NREL is a national laboratory of the U.S. Department of Energy, Office of Energy 

Efficiency & Renewable Energy, operated by the Alliance for Sustainable Energy, LLC.

Contract No. DE-AC36-08GO28308

U.S. Department of Energy 

Commercial Reference 

Building Models of the 

National Building Stock

Michael Deru, Kristin Field, Daniel Studer,

Kyle Benne, Brent Griffith, and Paul Torcellini

National Renewable Energy Laboratory

Bing Liu, Mark Halverson, Dave Winiarski,

and Michael Rosenberg

Pacific Northwest National Laboratory

Mehry Yazdanian

Lawrence Berkeley National Laboratory

Joe Huang

Formerly of Lawrence Berkeley National Laboratory

Drury Crawley

Formerly of the U.S. Department of Energy

Technical Report

NREL/TP-5500-46861

February 2011
NREL is a national laboratory of the U.S. Department of Energy, Office of Energy 

Efficiency & Renewable Energy, operated by the Alliance for Sustainable Energy, LLC.

National Renewable Energy Laboratory

1617 Cole Boulevard

Golden, Colorado 80401

303-275-3000 • www.nrel.gov

Contract No. DE-AC36-08GO28308

U.S. Department of Energy 

Commercial Reference 

Building Models of the 

National Building Stock

Michael Deru, Kristin Field, Daniel Studer,

Kyle Benne, Brent Griffith, and Paul Torcellini

National Renewable Energy Laboratory

Bing Liu, Mark Halverson, Dave Winiarski,

and Michael Rosenberg

Pacific Northwest National Laboratory

Mehry Yazdanian

Lawrence Berkeley National Laboratory

Joe Huang

Formerly of Lawrence Berkeley National Laboratory

Drury Crawley

Formerly of the U.S. Department of Energy

Prepared under Task No. BEC71304

Technical Report

NREL/TP-5500-46861

February 2011
NOTICE

This report was prepared as an account of work sponsored by an agency of the United States government. 

Neither the United States government nor any agency thereof, nor any of their employees, makes any warranty, 

express or implied, or assumes any legal liability or responsibility for the accuracy, completeness, or usefulness of 

any information, apparatus, product, or process disclosed, or represents that its use would not infringe privately 

owned rights. Reference herein to any specific commercial product, process, or service by trade name, 

trademark, manufacturer, or otherwise does not necessarily constitute or imply its endorsement, recommendation, 

or favoring by the United States government or any agency thereof. The views and opinions of authors 

expressed herein do not necessarily state or reflect those of the United States government or any agency thereof.

Available electronically at http://www.osti.gov/bridge

Available for a processing fee to U.S. Department of Energy

and its contractors, in paper, from:

U.S. Department of Energy

Office of Scientific and Technical Information

P.O. Box 62

Oak Ridge, TN 37831-0062

phone: 865.576.8401

fax: 865.576.5728

email: mailto:reports@adonis.osti.gov

Available for sale to the public, in paper, from:

U.S. Department of Commerce

National Technical Information Service

5285 Port Royal Road

Springfield, VA 22161

phone: 800.553.6847

fax: 703.605.6900

email: orders@ntis.fedworld.gov

online ordering: http://www.ntis.gov/help/ordermethods.aspx

Cover Photos: (left to right) PIX 16416, PIX 17423, PIX 16560, PIX 17613, PIX 17436, PIX 17721

Printed on paper containing at least 50% wastepaper, including 10% post consumer waste.
iii

Executive Summary

The U.S. Department of Energy (DOE) Building Technologies program has set aggressive goals

for energy efficiency improvements in buildings that will require collaboration between the DOE 

laboratories and the building industry. This report details the development of standard or 

reference energy models for the most common commercial buildings to serve as starting points 

for energy efficiency research. These models represent reasonably realistic building

characteristics and construction practices. Fifteen commercial building types and one 

multifamily residential building were determined by consensus between DOE, the National 

Renewable Energy Laboratory, Pacific Northwest National Laboratory, and Lawrence Berkeley 

National Laboratory, and represent approximately two-thirds of the commercial building stock. 

The reference buildings provide a common starting point to measure the progress of DOE energy 

efficiency goals for commercial buildings. The models of the reference buildings are used for 

DOE commercial buildings research to assess new technologies; optimize designs; analyze 

advanced controls; develop energy codes and standards; and to conduct lighting, daylighting, 

ventilation, and indoor air quality studies. 

The input parameters for the building models came from several sources. Some were determined 

from ASHRAE Standards 90.1-2004, 62.1-2004, and 62-1999 for new construction and Standard 

90.1-1989 for post-1980 construction; others were determined from studies of data and standard 

practices. National weighting factors are needed for each model in each location, so the relative 

importance of each can be factored into nationwide analyses. These factors characterize the 

number of buildings that are similar to each reference building type in each location. 
iv

Acronyms and Abbreviations

ACH air changes per hour

AEDG Advanced Energy Design Guide

AF area factor

ANSI American National Standards Institute

ASHRAE American Society of Heating, Refrigerating and Air-Conditioning Engineers

CAV constant air volume

CBECS Commercial Buildings Energy Consumption Survey

COP coefficient of performance

DOE U.S. Department of Energy

EER energy efficiency ratio

FCU fan coil unit

GGHC Green Guide for Health Care

HSPF heating seasonal performance factor

HVAC heating, venting, and air conditioning

IESNA Illuminating Engineering Society of North America

ILD internal load density

IRAC individual room air conditioner

ISH individual space heater

LBNL Lawrence Berkeley National Laboratory

LPD lighting power density

MZ multizone

NREL National Renewable Energy Laboratory

OA outside air

PACU packaged air-conditioning unit

PBA principal building activity

PNNL Pacific Northwest National Laboratory

PTAC packaged terminal air conditioner

PTHP packaged terminal heat pump

SAMSON solar and meteorological surface observational network

SEER seasonal energy efficiency ratio

SHGC solar heat gain coefficient

SHW service hot water

SS split system

SSPC standing standards project committee

SZ single zone

VAV variable air volume

WLCNS wall construction
v

Contents

Executive Summary.......................................................................................................................iii

Acronyms and Abbreviations ........................................................................................................ iv

Contents.......................................................................................................................................... v

Figure ............................................................................................................................................ vii

Tables............................................................................................................................................ vii

1.0 Introduction.......................................................................................................................... 1

2.0 Project Scope ....................................................................................................................... 2

2.1 Intended Uses of the Reference Building Models............................................................ 2

2.2 Uses Not Intended for the Reference Building Models ................................................... 2

3.0 Previous Work ..................................................................................................................... 3

4.0 Overall Approach................................................................................................................. 5

4.1 Determining Building Types............................................................................................ 5

4.2 Determining Locations..................................................................................................... 6

5.0 Energy Model Development................................................................................................ 8

5.1 Program............................................................................................................................ 8

5.1.1 Occupancy .................................................................................................................... 9

5.1.2 Ventilation .................................................................................................................. 11

5.1.3 Plug and Process Loads.............................................................................................. 14

5.1.4 Elevators..................................................................................................................... 14

5.1.5 Commercial Kitchens................................................................................................. 15

5.1.6 Service Hot Water Demand........................................................................................ 17

5.1.7 Schedules.................................................................................................................... 18

5.1.8 Utility Tariffs.............................................................................................................. 19

5.2 Form ............................................................................................................................... 19

5.3 Fabric.............................................................................................................................. 20

5.3.1 Envelope Constructions.............................................................................................. 20

5.3.2 Infiltration................................................................................................................... 29

5.4 Equipment ...................................................................................................................... 30

5.4.1 Interior Lighting ......................................................................................................... 30

5.4.2 Exterior Lights............................................................................................................ 31

5.4.3 HVAC Equipment ...................................................................................................... 32
vi

5.4.4 Fan Efficiencies.......................................................................................................... 38

5.4.5 Cooling Equipment Efficiencies................................................................................. 40

5.4.6 Refrigeration............................................................................................................... 40

6.0 Weighting Factors.............................................................................................................. 45

7.0 Conculsions........................................................................................................................ 47

8.0 References.......................................................................................................................... 48

Appendix A: Reference Building Internal Loads ......................................................................... 52

Appendix B: Schedules................................................................................................................. 70
vii

Figure

Figure 1 Climate zone classification.............................................................................................. 7

Tables

Table 1 Categorization of 2003 CBECS Data for Reference Building Models........................................... 6

Table 2 Selected Commercial Building Reference Model Locations.......................................................... 7

Table 3 Building Energy Model Input Categories....................................................................................... 8

Table 4 Occupancy by Space Type............................................................................................................ 10

Table 5 Outside Air Requirements (IP units)............................................................................................. 12

Table 6 Outside Air Requirements (SI units)............................................................................................. 13

Table 7 Plug and Process Load References............................................................................................... 14

Table 8 Number of Elevators Installed and Motor Power ......................................................................... 15

Table 9 Commercial Kitchen Loads .......................................................................................................... 16

Table 10 Distribution of Kitchen Loads in Zone Energy Balance............................................................. 16

Table 11 Peak Service Hot Water Demand and Data Sources................................................................... 17

Table 12 Reference Building Model Schedule Starting Points.................................................................. 18

Table 13 Reference Building Form Assignments...................................................................................... 19

Table 14 Sources for Reference Building Form Data................................................................................ 20

Table 15 Relationship of CBECS Roof Descriptions and Standard 90.1 Roof Constructions.................. 21

Table 16 Relationships Between CBECS Wall Descriptions and Standard 90.1 Wall Constructions ...... 22

Table 17 Recommended Roof Constructions by Building Type ............................................................... 23

Table 18 Recommended Wall Constructions by Building Type ............................................................... 24

Table 19 Roof U-Values (Btu/h·ft2

·oF) by Reference Building Vintage.................................................... 25

Table 20 Steel Frame Wall U-Values (Btu/h·ft2

·oF) by Reference Building Vintage................................ 25

Table 21 Mass Wall U-Values (Btu/h·ft2

·oF) by Reference Building Vintage........................................... 26

Table 22 Unheated Slab-On-Grade Floor Insulation by Reference Building Vintage R-Value 

(h·ft2

·oF/Btu) for 24-in. Vertical Insulation ......................................................................... 26

Table 23 Underground Wall Insulation by Reference Building Vintage R-Value (h·ft2

·oF/Btu)............... 27

Table 24 Window Overall U-Value (Btu/h·ft2

·oF) by Reference Building Vintage................................... 27

Table 25 Window Solar Heat Gain Coefficient by Reference Building Vintage ...................................... 28

Table 26 Reference Building Lighting Assumptions................................................................................. 31

Table 27 Exterior Lighting Assumptions................................................................................................... 32

Table 28 Parking Lot Lighting Levels....................................................................................................... 32

Table 29 HVAC Equipment Types for Post-1980 and New Construction ................................................ 33

Table 30 HVAC Equipment Types for Pre-1980 Construction ................................................................. 34
viii

Table 31 Estimated Unitary Cooling Equipment Efficiencies for Pre-1980 Construction ........................ 35

Table 32 Estimated Water Chilling Equipment Efficiencies for Pre-1980 Construction .......................... 37

Table 33 Estimated Packaged Terminal Cooling Equipment Efficiencies for Pre-1980 Construction ..... 37

Table 34 Estimated Space Heating Equipment Efficiencies for Pre-1980 Construction........................... 38

Table 35 Estimated Water Heating Equipment Efficiencies for Pre-1980 Construction........................... 38

Table 36 Fan System Inputs....................................................................................................................... 39

Table 37 Walk-In Refrigeration System Descriptions (IP Units).............................................................. 41

Table 38 Walk-In Refrigeration System Descriptions (SI Units).............................................................. 42

Table 39 Supermarket Refrigeration System Descriptions (IP Units)....................................................... 43

Table 40 Supermarket Refrigeration System Descriptions (SI Units)....................................................... 43

Table 41 Supermarket Compressor Descriptions....................................................................................... 44

Table 42 New Construction Reference Building Weighting Factors......................................................... 46

Table A-1 Reference Building Zone Internal Loads (IP units).................................................................. 52

Table A-2 Reference Building Zone Internal Loads (SI units).................................................................. 61

Table B-1 Quick Service Restaurant Hourly Operation Schedules........................................................... 70

Table B-2 Hospital Hourly Operation Schedules....................................................................................... 72

Table B-3 Large Hotel Hourly Operation Schedules................................................................................. 75

Table B-4 Large Office Hourly Operation Schedules................................................................................ 78

Table B-5 Medium Office Hourly Operation Schedules ........................................................................... 80

Table B-6 Midrise Apartment Hourly Operation Schedules...................................................................... 83

Table B-7 Outpatient Health Care Hourly Operation Schedules............................................................... 85

Table B-8 Primary School Hourly Operation Schedules........................................................................... 87

Table B-9 Retail Hourly Operation Schedules .......................................................................................... 90

Table B-10 Secondary School Hourly Operation Schedules..................................................................... 91

Table B-11 Full Service Restaurant Hourly Operation Schedules............................................................. 95

Table B-12 Small Hotel Hourly Operation Schedules............................................................................... 97

Table B-13 Small Office Hourly Operation Schedules............................................................................ 100

Table B-14 Strip Mall Hourly Operation Schedules................................................................................ 102

Table B-15 Supermarket Hourly Operation Schedules............................................................................ 103

Table B-16 Warehouse Hourly Operation Schedules.............................................................................. 107
1

1.0 Introduction

The U.S. Department of Energy (DOE) Building Technologies program has set aggressive goals

for energy efficiency improvements in buildings. This goal will require collaboration between 

the DOE laboratories and the building industry. Several analysis activities are under way to

determine the best paths forward. Coordinating research activities and tracking progress require 

common points of reference. 

The purpose of this project was to develop standard or reference building energy models for the 

most common commercial buildings to serve as starting points for analysis related to energy 

efficiency research. These models represent realistic building characteristics and construction 

practices. Fifteen commercial building types and one multifamily residential building (see Table 

1 on page 14) were determined by consensus between DOE, the National Renewable Energy 

Laboratory (NREL), Pacific Northwest National Laboratory (PNNL), and Lawrence Berkeley 

National Laboratory (LBNL). These represent approximately two-thirds of the commercial 

building stock. The remaining one-third is composed of several building types that are not easily 

defined by a small number of models; however, some are similar to one or more of the 16 

reference building types. 

There are three versions of the reference building models for each building type: new 

construction, post-1980 construction, and pre-1980 construction. All have the same building 

form and area and the same operation schedules. The differences are reflected in the insulation

values, lighting levels, and HVAC equipment types and efficiencies. The new construction 

models comply with the minimum requirements of ANSI/ASHRAE/IESNA Standard 90.1-2004

(ASHRAE 2004a), the post-1980 models meet the minimum requirements of Standard 90.1-1989

(ASHRAE 1989), and the pre-1980 models are built to a set of requirements developed from 

previous standards and other studies of construction practices.

The reference building models are described in detail in this report and are available as 

EnergyPlus input files (http://commercialbuildings.energy.gov/reference_buildings.html). 

Spreadsheet scorecards document the model parameters and annual energy performance for each 

building type and location. 

Throughout the development of the reference buildings, the DOE Building Energy Codes 

Program, the ASHRAE simulation working group, and Standard 90.1 subcommittees have 

provided in-depth review of the underlying assumptions.
2

2.0 Project Scope

The reference building models cover 16 building types and 16 U.S. locations. They directly 

characterize more than 60% of the commercial building stock and are very similar to other 

commercial building types. The models are fully defined in the spreadsheet scorecards and are 

available as EnergyPlus input files. 

2.1 Intended Uses of the Reference Building Models

The purpose of these models is to represent new and existing buildings. The reference building 

models will be used for DOE commercial buildings research to assess new technologies;

optimize designs; analyze advanced controls; develop energy codes and standards; and to

conduct lighting, daylighting, ventilation, and indoor air quality studies. They also provide a 

common starting point to measure the progress of DOE energy efficiency goals for commercial 

buildings. DOE’s Building Energy Code Program and PNNL use these models for the 

analytical support in the development of new versions of ASHRAE Standard 90.1. The models 

provide consistency in modeling approaches and implementation across commercial buildings.

2.2 Uses Not Intended for the Reference Building Models

These reference building models are not intended to represent energy use in any particular 

building. Rather, they are hypothetical models with ideal operations that meet certain minimum 

requirements.

The reference building model definitions are not intended to act as targets to rate the energy 

performance of single existing or proposed buildings. The models and weighting factors are not 

appropriate for analysis at the state level, as the datasets used to generate the models and the

weighting factors are too small to form a valid statistical model at this level. Variations of these 

models and weighting factors could be created for such purposes, but that is not the objective of 

this project.
3

3.0 Previous Work

Several projects have created prototypical building energy models. The most familiar are from 

LBNL, which developed a series of prototypical buildings over several years. Huang et al. 

(1991) and Huang and Franconi (1999) present extensive summaries of work in this area; Huang 

et al. (2005) present an analysis of 1999 building data. Three recent efforts to develop 

prototypical energy models of buildings include a set of standardized energy simulation models 

for commercial buildings from the University of Massachusetts (Stocki et al. 2005), a residential 

building benchmark model from the DOE Building America program (Hendron 2007), and an 

assessment of the entire commercial building stock by NREL (Griffith et al. 2007). Projects that 

focused on single building types were carried out to create the Advanced Energy Design Guides

(AEDGs) for small office, small retail, warehouses, K–12 schools, highway lodging, and small 

healthcare (ASHRAE 2009). 

Huang et al. (1991) developed 481 prototypical commercial buildings (37 building types and 

13 locations) for a market assessment of cogeneration systems. The building types, sizes, and 

locations were selected based on the best potential to use cogeneration. The purpose of the 

project was to model the energy use in existing commercial building stock as closely as 

reasonable. The paper presents a summary of building characteristics databases, engineering 

studies, characterizations, and prototypes for energy simulations. The data included the 

Nonresidential Building Energy Consumption Survey, which later became the Commercial

Buildings Energy Consumption Survey (CBECS) (EIA 2005), and F.W. Dodge building stock 

and forecast data (McGraw-Hill 2005). They completed sensitivity analyses to better understand 

the effects of building size, external wall models, thermal zoning, and HVAC types on the 

simulated energy use.

Huang and Franconi (1999) estimated the heating and cooling loads in existing commercial 

buildings by component and the efficiencies of the equipment used to meet those loads. They 

used 120 prototypical buildings covering 12 building types of old and new construction. The 

models were updated versions of the 1991 Huang et al. models based on 1989 CBECS data. The 

models were extrapolated to represent the regional and national building stock with weighting 

factors derived from the 1992 CBECS. 

Stocki et al. (2005) present a set of standardized assumptions for commercial building energy 

analyses. They define seven building types: large office, small office, retail, education, 

apartment, small hotel, and hospital. These are meant to represent typical commercial buildings; 

however, there is little justification for the types chosen. The building sizes were based on work 

by Huang and Franconi (1999). Energy-related parameters conform to ASHRAE Standards 

90.1-2001 (ASHRAE 2001) and 62.1-1999 (ASHRAE 1999). These models could be used to 

analyze energy performance of any of the seven building types in any climate; however, there is 

no method to extend the results beyond each type and size.

The Building America benchmark model (Hendron 2007) provides a common baseline for 

determining energy savings of new residential buildings. Hourly energy simulations are used to 

determine the savings. The size and location of the benchmark (baseline) building are set to 

match the proposed building, but everything else is defined by a set of modeling rules. The 

operating schedules are clearly defined and are used for both building simulations.
4

Griffith et al. (2007) completed an assessment of the commercial building sector for the potential 

to reach net zero energy. They autogenerated energy simulation models for all the buildings in 

1999 CBECS (EIA 2002), except refrigerated warehouses. This effort resulted in5,375 models

which were used to examine potentials of different technology scenarios for the commercial 

building stock. While robust, the number of buildings results in a computational burden for 

extensive analysis. 
5

4.0 Overall Approach

It is impractical to model every new commercial building, or even to represent every building 

sub-sector, so we selected a small number of prevalent building types and developed weighting 

factors to represent a percentage of the commercial building stock. A goal was set to represent 

70% of the U.S. commercial building floor area.

National data from the 2003 CBECS (EIA 2005) were used to determine the appropriate, average 

mix of representative buildings. We selected 16 building types and developed weighting factors 

to adjust for the percentage of the building stock represented by each building type for 16 

locations. This mix of buildings and locations demonstrates the climatic and geographic effects 

in each construction vintage. The three vintages of 16 building types in 16 locations result in 

768 models. 

Creating energy simulation input files is tedious and time consuming, and mistakes are common. 

Analysis activities of the national building sub-sectors can involve creating hundreds—or even 

thousands—of input files. To alleviate some of the workload and minimize the potential for 

mistakes, we developed computer programs to create the input files for the energy simulations 

based on sets of easily implemented rules. The input files by location are autocreated from a 

seed file for each building type and vintage based on rules from appropriate energy efficiency 

standards for climate-variable parameters.

4.1 Determining Building Types

The best publicly available data on commercial buildings are from CBECS (EIA 2005), for 

which the 2003 version contains 5,215 buildings. The CBECS variables PBA8 and PBAplus8 

separate the commercial sector into 29 categories and 51 subcategories based on principal 

building activity (PBA). Analysis of the CBECS data provided the project team with the most 

typical building types, and the final set of building types was selected by consensus among DOE, 

NREL, LBNL, and PNNL. The set of 15 building types from CBECS is listed in Table 1, along 

with the PBA numbers. A midrise apartment building model is also included to total 16 building 

types. Multifamily housing buildings are not included in CBECS, and the midrise apartment 

model was developed from other data in a separate PNNL study (Gowri et al. 2007). 

This set of 15 commercial building types represents 3,279 buildings (of 5,215) from the full 

CBECS dataset. This subset represents 44 billion ft2 (4.1 billion m2

) or 62% of the total 

weighted floor area in the survey (64% if the vacant buildings are removed from the total) and 

65% of the total energy consumption. The remaining CBECS building types include buildings 

that vary significantly in size, internal loads, and operation; several building types would need to 

be added to reach the 70% goal. Religious worship buildings are the next-largest group of 

buildings, which would raise the percentage of the total weighted floor area to 67%. However, 

they represent 74% of the new construction from 2003 to 2007 contained in the McGraw-Hill 

Construction Starts Database (Jarnagin and Bandyopadhyay 2010). 
6

Table 1 Categorization of 2003 CBECS Data for Reference Building Models

Name PBA8 PBAPLUS8

Small Office 2 2, 3, 4, 5, 6, 7

Medium Office 2 2, 3, 4, 5, 6, 7

Large Office 2 2, 3, 4, 5, 6, 7

Primary School 14 28

Secondary School 14 29

Stand-Alone Retail 25 42

Strip Mall 23 50

Supermarket 6 14

Quick Service Restaurant 15 32

Full Service Restaurant 15 33

Small Hotel 18 39

Large Hotel 18 38

Hospital 13 35

Outpatient Healthcare 8 18,19

Warehouse 5 9, 10

Midrise Apartment N/A N/A

4.2 Determining Locations

Locations were selected to represent significant portions of the existing building stock and all

U.S. climate zones. Population is a good indicator of building distribution; however, if it were

the only criterion, some climate zones would not be represented. Approximately 78% of the 

population is located in five of the 15 climate zones. To represent all U.S. climate zones and the 

highest building densities, we selected the most populous cities in each climate zone.

Briggs et al. (2003) developed a climate zone classification system for DOE and ASHRAE 

Standard 90.1-2004 based on SAMSON (NCDC 1993) weather data, as shown in Figure 1. An 

important characteristic of these climate zones is that they tend to run in east–west bands across 

the country; subdivisions for moist, dry, and marine divide these bands. As part of this effort, 

PNNL developed a set of “typical” locations (cities) based on their representativeness in each 

climate zone. The selections had little to do with population or number of buildings. 

We selected a revised set of locations as a balance of the representativeness of the climate and 

the number of buildings in each climate zone (see Table 2). Two locations were selected for 

climate zone 3B because they represent different climates within one zone, which is evident from 

the reference building model energy simulation results. These subclimate zones are designated 

as “3B-CA” for the California coast and “3B-other” for the remaining part of climate zone 3B.
7

Figure 1 Climate zone classification

(Credit: Briggs et al. [2003]; DOE [2005])

Table 2 Selected Commercial Building Reference Model Locations

Number Climate Zone Representative City TMY2 Weather file location

1 1A Miami, Florida Miami, Florida

2 2A Houston, Texas Houston, Texas

3 2B Phoenix, Arizona Phoenix, Arizona

4 3A Atlanta, Georgia Atlanta, Georgia

5 3B-CA Los Angeles, California Los Angeles, California

6 3B-other Las Vegas, Nevada Las Vegas, Nevada

7 3C San Francisco, California San Francisco, California

8 4A Baltimore, Maryland Baltimore, Maryland

9 4B Albuquerque, New Mexico Albuquerque, New Mexico

10 4C Seattle, Washington Seattle, Washington

11 5A Chicago, Illinois Chicago-O’Hare, Illinois

12 5B Denver, Colorado Boulder, Colorado

13 6A Minneapolis, Minnesota Minneapolis, Minnesota

14 6B Helena, Montana Helena, Montana

15 7 Duluth, Minnesota Duluth, Minnesota

16 8 Fairbanks, Alaska Fairbanks, Alaska
8

5.0 Energy Model Development

The intent of the reference building models is to characterize the energy performance of typical 

building types under typical operations. Detailed building energy models require several pieces 

of information that are not available from standard data sources; therefore, information from 

several sources was combined in a sensible way to represent “typical” performance. To better 

organize the efforts, we divided the model inputs into program, form, fabric, and equipment 

(see Table 3).

Table 3 Building Energy Model Input Categories

Program Form Fabric Equipment

Location Number of floors Exterior walls Lighting 

Total floor area Aspect ratio Roof HVAC system types

Plug and process loads Window fraction Floors Water heating equipment 

Ventilation requirements Window locations Windows Refrigeration

Occupancy Shading Interior partitions Component efficiency

Space environmental conditions Floor height Internal mass Control settings

Service hot water demand Orientation Infiltration

Operating schedules

The program and form for the small office, schools, warehouse, small hotel, and outpatient 

healthcare were taken, with slight modifications, from the work on the AEDGs for these building 

types. PNNL developed the midrise apartment model for its work to support the development of

Standard 90.1. The program and form of the remaining models were developed from analysis of 

CBECS (EIA 2005) and Time-Saver Standards for Building Types (DeChiara and Crosbie 2001)

and from experience with these building types.

The fabric and equipment parameters set by energy standards were determined from ASHRAE 

Standards 90.1-2004 (ASHRAE 2004a), 62.1-2004 (ASHRAE 2004b), and 62-1999 (ASHRAE 

1999) for new construction and Standard 90.1-1989 (ASHRAE 1989) for post-1980 construction. 

NREL, PNNL, and LBNL performed research to determine the remaining model inputs. PNNL 

completed a series of reports analyzing 2003 CBECS and past energy standards to determine 

many of the energy model parameters used in these models. Winiarski et al. (2007a; 2007b; 

2008) published two reports and a conference paper that analyzed envelope construction and 

some building form characteristics. The HVAC system types were determined from the results 

of a study by Winiarski et al. (2006) of system types and efficiencies for pre-1980 and post-1980 

models and from input from the standing standards project committee (SSPC) 90.1 Simulation 

Working Group and Mechanical Subcommittee for the new construction models. Throughout 

the development of the reference building models, the DOE Building Energy Codes Program, the 

ASHRAE simulation working group, and SSPC 90.1 subcommittees have provided in-depth 

review of the models and the underlying assumptions.

5.1 Program

The building program includes the activity, location, occupancy, plug and process loads, service 

water heating demand, and schedules. The PBAs were determined during the process of 

analyzing the national building data (see Table 1). The reference building models are intended to
9

look much more like real buildings as compared to the generic boxes often used for energy 

simulation studies. LBNL developed the original geometry characterization of the reference

building models (except for the midrise apartment), including the shape, floor area, number of 

floors, and thermal zoning based on previous work and analysis of 2003 CBECS (EIA 2005). 

Nine models were completely changed and modifications were made to the other models based 

on input from industry and further data analysis. PNNL, NREL, and the AEDG project

committees developed the models for the small office, primary and secondary schools, 

warehouse, small hotel, and outpatient health care for the AEDGs for these respective building 

types (ASHRAE 2009). NREL developed the stand-alone retail and supermarket reference

building models based on work with national retailers and CBECS. NREL and PNNL developed 

the strip mall model from CBECS data and from a review of actual strip mall layouts. 

Table 13 lists the building floor areas and many form parameters. Appendix A lists the zone 

level program parameters in IP units (Table A-1) and SI units (Table A-2) for each model. 

5.1.1 Occupancy

Occupancy information is included in CBECS; however, close inspection reveals that these data 

are unreliable. For example, office building occupancy (based on the number of workers on the 

main shift from the 1999 CBECS [EIA 2002]) ranges from 334 ft2

/person to 300,000 ft2/person 

(31 m2

/person to 27,871 m2/person) with a mean of more than 25,000 ft2/person (2,323 

m

2

/person). The occupancy rates for the reference building models were instead taken from the 

AEDG studies for the appropriate building types and from the default occupancy rates in 

Standard 62.1-2004 (ASHRAE 2004b) following a recommendation by the ASHRAE 90.1 

Simulation Working Group. Changes were made for dining, kitchen, storage, and shipping and 

receiving areas, where these occupancy rates exceed the 2003 International Building Code 

maximum (ICC 2003). The occupancy rates by space type are listed in Table 4, either as the 

total number of occupants per space or as occupant density. Appendix A lists occupancy by 

zone for each model.

Pless et al. (2007) documented the primary school model with 650 students and the secondary 

school with 1200 students; however, the occupancy densities and schedules from the energy 

models resulted in much higher numbers of students. The classroom occupancy schedules were 

adjusted by factors of 0.75 for the primary school and 0.70 for the secondary school to arrive at

the student numbers documented in the project report.

The hotel guest rooms were assumed to have 1.5 occupants each, and occupancy rates for the 

two hotel models were assumed to be 65% to align with the industry average occupancy rate and 

Jiang et al. (2008). Rooms were randomly assigned occupants in the small hotel model so 50 of 

the 77 rooms are occupied. The occupancy, lighting, and hot water schedules for the unoccupied 

rooms were set to zero. The plug load schedule was set to a constant value of 20% for all rooms. 

The thermal zoning and the use of multipliers in the large hotel model do not allow for this type 

of control; therefore, a set of schedules was created to reduce the occupancy and loads to match 

the 65% occupancy rate across all guest rooms. 
10

Table 4 Occupancy by Space Type

Space Type

Occupancy 

per Space

Occupancy

ft Data Source 2/person m2/person

Apartment 3.0 – – Gowri et al. 2007

Auditorium seating area – 10.8 1 Pless et al. 2007

Cafeteria/FF dining – 15 1.4 ICC 2003

Classrooms – 43 4 Pless et al. 2007

Corridor (school) – 107.6 10 Pless et al. 2007

Corridor (public spaces) – 1000 93 Engineering judgment

Hotel guest room 1.5 – – Jiang et al. 2008

Gym (primary school) – 35.8 3.3 Pless et al. 2007

Gym (secondary school) – 10.8 1.0 Pless et al. 2007

Gym, auxiliary (secondary school) – 35.8 3.3 Pless et al. 2007

Kitchen (commercial) – 200 18.6 ICC 2003

Laundry – 250 23. Jiang et al. 2008

Library/Media center – 46.8 4.4 Pless et al. 2007

Lobby (school) 0.0 – – Engineering judgment

Lobby (hotel) – 33.3 3 ASHRAE 2004b

Lobby (office building) – 100 9.3 ASHRAE 2004b

Office – 200 18.6 ASHRAE 2004b

Office (apartment) 2.0 – – Gowri et al. 2007

Office (school) – 215 20 Pless et al. 2007

Office (warehouse) 5.0 – – Liu et al. 2007

Reception areas – 33.3 3.1 ASHRAE 2004b

Restaurant dining rooms – 15 ICC 2003

Restroom (school) – 1076 100 Pless et al. 2007

Sales – 66.7 6.2 ASHRAE 2004b

Shipping/Receiving – 300 28 ICC 2003

Storage – 300 28 ICC 2003

Supermarket – 125 11.6 ASHRAE 2004b

Warehouse 0.0 – – Liu et al. 2007

Hospital spaces

Critical and intensive care – 50 4.7 Doebber et al. 2009

ER exam rooms and triage – 50 4.7 ASHRAE 2004b

Laboratory – 200 18.6 GGHC 2007

Nurse’s station/waiting rooms – 750 69.7 Engineering judgment

Operating/surgical cystoscopic rooms – 200 18.6 GGHC 2007

Patient room – 200 18.6 GGHC 2007

Physical therapy – 200 18.6 GGHC 2007

Radiology 200 18.6 GGHC 2007

Outpatient spaces

Nurse’s station – 50 4.7 GGHC 2007

Operating room – 50 4.7 GGHC 2007

Procedure room – 50 4.7 GGHC 2007

Exam room – 50 4.7 GGHC 2007

Clean/soiled areas – 50 4.7 GGHC 2007

Recovery room – 50 4.7 GGHC 2007
11

5.1.2 Ventilation

The ventilation or outside air (OA) requirements are listed by space type in Table 5 (IP units) 

and Table 6 (SI units). Standard 90.1-2004 refers to Standard 62-1999 as a normative reference, 

so the ventilation requirements from Standard 62-1999 Table 2 are used (ASHRAE 1999). The 

occupancy rates were taken from the AEDG technical support documents for those buildings 

with AEDGs and the default occupancy rates from 62.1-2004 for other building types as 

recommended by the Standard 90.1 Simulation Working Group. The occupancy rates in 

Standard 62.1-2004 are considered to be more realistic than those in 62-1999. We assumed that 

the ventilation requirements are the same for all vintages of reference building models because 

reliable data for older buildings are not available. We will reevaluate this assumption as more 

information about existing buildings becomes available.

The OA requirements for the hospital and the outpatient facility were determined from the 2007 

Green Guide for Health Care (GGHC 2007), the 2001 Guidelines for Design and Construction 

of Hospital and Health Care Facilities (AIA 2001), and from Standard 62-1999. 

A brief discussion of the ventilation design practices for hospitals is worthwhile. Most hospitals 

are designed to comply with AIA (2001). This document is updated periodically; e.g., 1987, 

1992, 1996, 2001, and 2006. The Centers for Medicare and Medicaid Services references the 

2001 edition, but most consultants design to the current version. Compliance is law in many 

states, and is a requirement for reimbursement for Medicare and Medicaid. Regardless, very few 

hospitals choose to not accept Medicare and Medicaid patients. In 2004 most designs probably 

would have complied with the 2001 edition. Today most are shifting to the 2006 edition, 

although it is not generally required by law. 
12

Table 5 Outside Air Requirements (IP units)

Space Type

Default 

Occupancy OA Total OA OA Data Sources

ft2/person cfm/person cfm/ft2 cfm/ft2 ACH Occupancy Ventilation

Auditorium seating area 10.8 15 – 1.39 – Pless et al. 2007 ASHRAE 1999

Bath (cfm/room) – 20 – – – ASHRAE 1999

Cafeteria/FF dining 15 20 – 1.33 – ICC 2003 ASHRAE 1999

Classrooms 43.1 15 – 0.35 – Pless et al. 2007 ASHRAE 1999

Corridor (school) – – 0.10 0.10 – – ASHRAE 1999

Corridor (public spaces) – – 0.05 0.05 – – ASHRAE 1999

Hotel guest room (cfm/room) – 30 – – – ASHRAE 1999

Gym (primary school) 35.8 20 – 0.56 – Pless et al. 2007 ASHRAE 1999

Gym (secondary school) 10.8 20 – 1.86 – Pless et al. 2007 ASHRAE 1999

Kitchen (commercial) 200 15 – 0.075 – ICC 2003 ASHRAE 1999

Kitchen (residential, cfm/room) – 25 – – – – ASHRAE 1999

Living areas (residential) – 15 – – – – ASHRAE 1999

Lobby (school, treat as a corridor) – 0.10 0.10 – – ASHRAE 1999

Lobby (hotel) 33.3 20 – 0.60 – ASHRAE 2004b ASHRAE 1999

Lobby (office building) 100 20 – 0.20 – ASHRAE 2004b ASHRAE 1999

Office 200 20 – 0.10 – ASHRAE 2004b ASHRAE 1999

Reception areas 33.3 15 – 0.45 – ASHRAE 2004b ASHRAE 1999

Restaurant dining rooms 15 20 – 1.33 – ICC 2003 ASHRAE 1999

Restroom (cfm/wc or urinal) – 50 – – – ASHRAE 1999

Sales 66.7 – 0.30 0.30 – ASHRAE 2004b ASHRAE 1999

Shipping/receiving 300 – 0.15 0.15 – ICC 2003 ASHRAE 1999

Storage 300 – 0.15 0.15 – ICC 2003 ASHRAE 1999

Supermarket 125 15 – 0.12 – ASHRAE 2004b ASHRAE 1999

Warehouse – – 0.05 0.05 – – ASHRAE 1999

ER waiting room – – – – ASHRAE 2004b – AIA 2001

Operating/surgical cystoscopic rooms – – – – Pless et al. 2007 – AIA 2001

Critical and intensive care – – – – ASHRAE 2004b – AIA 2001

Patient room – – – – ASHRAE 2004b – AIA 2001

Examination room 50 – 0.30 0.30 – ASHRAE 2004b GGHC 2007

Clean linens – – 0.30 0.30 – – GGHC 2007

Soiled linens – – 1.50 1.50 – – GGHC 2007

Nurse station – – 0.15 0.15 – – GGHC 2007

Physical therapy 50 – 0.30 0.30 – ASHRAE 2004b GGHC 2007

Radiology – – 0.30 0.30 – – GGHC 2007

Anesthesia storage – – 1.20 1.20 – – GGHC 2007
13

Table 6 Outside Air Requirements (SI units)

Space Type

Default 

Occupancy OA Total OA OA Data Sources

m2/person L/s/person L/s/m2 L/s/m2 ACH Occupancy Ventilation

Auditorium seating area 1.00 7.08 – 7.08 – Pless et al. 2007 ASHRAE 1999

Bath (cfm/room) – 9.44 – 0.00 – ASHRAE 1999

Cafeteria/FF dining 1.39 9.44 – 6.77 – ICC 2003 ASHRAE 1999

Classrooms 4.00 7.08 1.77 – Pless et al. 2007 ASHRAE 1999

Corridor (school) – – 0.51 0.51 – – ASHRAE 1999

Corridor (public spaces) – – 0.25 0.25 – – ASHRAE 1999

Hotel guest room (cfm/room) – 14.16 – – – – ASHRAE 1999

Gym (primary school) 3.33 9.44 – 2.83 – Pless et al. 2007 ASHRAE 1999

Gym (secondary school) 1.00 9.44 – 9.44 – Pless et al. 2007 ASHRAE 1999

Kitchen (commercial) 18.59 7.08 – 0.38 – ICC 2003 ASHRAE 1999

Kitchen (residential, cfm/room) – 11.80 – – – – ASHRAE 1999

Living areas (residential) – 7.08 – – – – ASHRAE 1999

Lobby (school, treat as a corridor) – 0.51 0.51 – – ASHRAE 1999

Lobby (hotel) 3.10 9.44 – 3.05 – ASHRAE 2004b ASHRAE 1999

Lobby (office building) 9.29 9.44 – 1.02 – ASHRAE 2004b ASHRAE 1999

Office 18.59 9.44 – 0.51 – ASHRAE 2004b ASHRAE 1999

Reception areas 3.10 7.08 – 2.29 – ASHRAE 2004b ASHRAE 1999

Restaurant dining rooms 1.39 9.44 – 6.77 – ICC 2003 ASHRAE 1999

Restroom (cfm/wc or urinal) 23.60 – – – ASHRAE 1999

Sales 6.20 – 1.52 1.52 – ASHRAE 2004b ASHRAE 1999

Shipping/receiving 27.88 – 0.76 0.76 – ICC 2003 ASHRAE 1999

Storage 27.88 – 0.76 0.76 – ICC 2003 ASHRAE 1999

Supermarket 11.62 7.08 – 0.61 – ASHRAE 2004b ASHRAE 1999

Warehouse – – 0.25 0.25 – – ASHRAE 1999

ER waiting room – – – – ASHRAE 2004b – AIA 2001

Operating/surgical cystoscopic rooms – – – – Pless et al. 2007 – AIA 2001

Critical and intensive care – – – – ASHRAE 2004b – AIA 2001

Patient room – – – – ASHRAE 2004b – AIA 2001

Examination room 4.65 – 1.52 1.52 – ASHRAE 2004b GGHC 2007

Clean linens – – 1.52 1.52 – – GGHC 2007

Soiled linens – – 7.62 7.62 – – GGHC 2007

Nurse station – – 0.76 0.76 – – GGHC 2007

Physical therapy 4.65 – 1.52 1.52 – ASHRAE 2004b GGHC 2007

Radiology – – 1.52 1.52 – – GGHC 2007

Anesthesia storage – – 6.10 6.10 – – GGHC 2007
14

5.1.3 Plug and Process Loads

Determining the plug or process load intensity is difficult because available measured data are

scarce. Thus, we had to make several assumptions based on experience with a small number of 

buildings, previous work by Huang et al. (1991), levels from ASHRAE (1989), and the AEDG 

series. The plug and process loads and schedules are determined at the zone level based on the 

activities in each zone. The models will be updated as new data become available. Appendix A 

lists all the plug loads by zone for each building model in IP and SI units. Table 7 lists the main

references for the plug and process loads by building type. Kitchen loads for all building models 

with kitchens are discussed in the Commercial Kitchen sections.

Table 7 Plug and Process Load References

Building/Zone Data Source

Small Office Engineering judgment

Medium Office Engineering judgment

Large Office Engineering judgment

Primary School Pless et al. 2007

Secondary School Pless et al. 2007

Stand-Alone Retail Engineering judgment

Strip Mall Engineering judgment

Supermarket Engineering judgment

Small Hotel Jiang et al. 2008

Large Hotel Huang et al. 1991

Hospital Doebber et al. 2009, GGHC 2007

Outpatient Healthcare Doebber et al. 2009, GGHC 2007

Warehouse Liu et al. 2007

Midrise Apartment Hendron 2007

The laundry facility loads for the hotels were modified from Jiang et al. (2008), who assumed 

60-lb (27-kg) commercial washing machines that use 3.4 Btu/h (1,390 W) of electricity per cycle 

and gas dryers that use 2.6 Btu/h (750 W) of electricity per cycle. They also assumed 9 lb (4.1 

kg) of laundry per room per day and that the washed laundry retains water equal to 87.5% of its 

dry weight. For the assumed 65% occupancy, the small hotel requires 8 loads per day and the 

large hotel requires 18 loads per day. To calculate gas use, we assumed a heat of vaporization of 

1000 Btu/lb (2,326 kJ/kg) of water and a thermal efficiency of the gas dryer of 80%. The total 

energy use for washing and drying was divided evenly over 8 hours. (See Appendix A for the 

electricity and gas loads for each space.)

5.1.4 Elevators

Elevators are included in all buildings with multiple floors. They are modeled in EnergyPlus as 

a zone load but labeled as “elevators,” so they are reported separately in the EnergyPlus output. 

The number of elevators in the reference building models was determined from rules of thumb 

presented by Beyer (2009) (see Table 8). The office buildings have one elevator for every 

45,000 ft2 (4,181 m2

), plus one service elevator for the large office building. The hotels have one 
15

elevator for every 75 rooms, and the large hotel includes one service elevator for every two 

public elevators, plus one additional elevator for the dining and banquet facilities on the top 

floor. The hospital has one public and one service elevator for every 100 beds (250 total), plus 

two elevators for the offices and cafeteria on the top floor. The outpatient healthcare model has

the minimum recommendation of two elevators. The apartment building has one elevator for 

every 90 units, and the secondary school has two elevators.

Table 8 Number of Elevators Installed and Motor Power

Building Type Number of 

Elevators

Motor Power

(w/each)

Medium Office 2 14,610

Large Office 12 18,537

Secondary School 2 14,610

Small Hotel 2 14,610

Large Hotel 6 18,537

Hospital 8 18,537

Outpatient Healthcare 3 14,610

Midrise Apartment 1 14,610

For buildings with fewer than six stories (counting the basement), we assumed the elevators use 

hydraulic motors with no over counter weighting, weigh 2,500 lb (1,134 kg), travel 150 fpm (46 

mpm), and have a mechanical efficiency of 58%. In this case, the heat gain was added to the 

first floor core zone. For buildings six stories and higher, we assumed the elevators use traction 

motors with 40% over counter weighting, weigh 2,500 lb (1,134 kg), travel 350 fpm (1.78 m/s), 

and have a mechanical efficiency of 64%. In this case, the heat gain was added to the top floor 

core zone. The following equation is used to calculate the motor power in horsepower (Baldor 

Electric Company 1998). The schedules were taken from ASHRAE (1989).

[ ]

m

W V OCW Motor HP ⋅η

⋅ ⋅ − = 33,0001

where

W = weight of car (lb)

V = speed of car (fpm)

OCW = over counter weight (fraction of car capacity)

ηm = mechanical efficiency of elevator (fraction)

5.1.5 Commercial Kitchens

Six reference buildings have commercial kitchens, and the supermarket has a deli and a bakery 

that use similar types of equipment. Commercial kitchens have high electric and gas equipment 

densities for refrigeration, food preparation, and dishwashing, and often have high ventilation 

requirements. The internal loads in kitchens can vary tremendously depending on the types and 

amounts of food served. The internal loads included in the reference buildings are shown in 

Table 9, along with the SHW and ventilation requirements. These loads represent the installed 
16

capacity; actual peak demand and total energy use are determined by applying the operating 

schedules in Appendix B. The electricity loads include reach-in refrigerators, and some of the 

electric food preparation load is assumed to be in the dining zones. Walk-in coolers and freezers 

are modeled as separate EnergyPlus objects and are discussed in the Refrigeration section. 

Table 9 Commercial Kitchen Loads

Building

Meals 

per 

Day

Gas 

Load 

(kW)

Electricity 

Load 

(kW)

Electricity 

in Dining 

Zone

SHW 

gal/h 

(L/h)

SHW 

Temp. at 

Fixture 

°F (°C)

Hooded 

Exhaust cfm 

(L/s)

Primary School 400 160 40 20% 100 (379) 120 (49) 3,300 (1,557)

Secondary School 600 242 60 20% 133 (503) 120 (49) 4,000 (1,888)

Supermarket Deli – 6 5 – 5 (19) 120 (49) –

Supermarket Bakery – 11 3 – 5 (19) 120 (49) 2,500 (1,180)

Quick Service Restaurant 800 150 50 30% 40 (151) 120 (49) 3,300 (1,557)

Full Service Restaurant 780 167 75 30% 133 (503) 120 (49) 4,000 (1,888)

Large Hotel 780 167 75 30% 133 (503) 120 (49) 4,000 (1,888)

Hospital 800 283 75 0% 150 (568) 120 (49) 5,300 (2,501)

We assume the kitchens in the full service restaurant, large hotel, and schools have similar loads 

and can be scaled with the estimated number of meals served each day. The kitchen electricity 

and gas process loads and the exhaust flow rates are based on information from Brown (2007),

Fisher (2003), Smith et al. (1999), Smith and Fisher (2001), data from the California Energy 

Commission (CEC 2004) and SGE (2004), a review of actual kitchen designs, and examination 

of annual utility data from more than 1000 operating commercial kitchens. Table 10 shows the 

energy distribution of the kitchen loads within the EnergyPlus zone energy balance. All gas 

appliances are assumed to be under exhaust hoods, so a high fraction of the energy is “lost” out 

the exhaust hood and not added to the space load. 

Table 10 Distribution of Kitchen Loads in Zone Energy Balance

Fraction

Gas

Equipment

Electrical 

Equipment Exhaust Hoods

Lost 0.7 0.20 1.0

Latent 0.1 0.25 0.0

Radiant 0.2 0.30 0.0

Convective 0.0 0.25 0.0

The kitchen exhaust rates are shown in the final column of Table 9. Transfer air from the dining 

zones is used for all or part of the make-up air requirements, depending on how much air is 

available from the dining areas. This transfer air is modeled with an EnergyPlus ZoneMixing 

object in the kitchen zone and a zero power exhaust fan in the dining zone. EnergyPlus version 

4.0 has two limitations that force a modeling workaround for the exhaust fans and make-up air: 
17

• Exhaust fans are controlled with an on–off schedule only, and cannot have a fractional 

schedule; therefore, the fans are assumed to run at full flow. 

• EnergyPlus does not account for the transfer air from adjacent zones when the OA

requirements are calculated. It determines the OA as the maximum of the exhaust fan 

flow rate and the minimum OA schedule multiplied by the peak OA flow rate without 

consideration of the transfer air. 

To work around this problem, we calculated the hourly energy use of the exhaust fans in a 

spreadsheet and entered it in the EnergyPlus model as an electricity load to the zones. The OA

requirements for the kitchens are set with the zone sizing object and an hourly schedule. 

5.1.6 Service Hot Water Demand

The peak service hot water (SHW) demand for each reference building space type is shown in 

Table 11, along with the temperatures at the fixture and the sources of data. These numbers are 

used in conjunction with the operating schedules to estimate the total hot water consumption. 

Hot water use in kitchens is included in the Commercial Kitchen section. Natural gas water 

heaters are used in all cases; storage tanks are kept at 140oF (60oC).

Table 11 Peak Service Hot Water Demand and Data Sources

Space Type

Use Rate

Temp. at 

Fixture

gal/h L/h oF oC Data Sources

Guest room (small hotel) 1.75 6.6 110 43 Jiang et al. 2008, ASHRAE 2007

Guest room (large hotel) 1.25 4.7 110 43 Jiang et al. 2008, ASHRAE 2007

Laundry (small hotel) 67.5 255.5 140 60 Jiang et al. 2008, ASHRAE 2007

Laundry (large hotel) 156.6 592.8 140 60 Jiang et al. 2008, ASHRAE 2007

Restrooms (primary school) 56.5 214.0 110 43 ASHRAE 2007

Restrooms (secondary school) 104.4 395.0 110 43 ASHRAE 2007

Gym (secondary school) 189.5 717.2 110 43 ASHRAE 2007

Small office 3.0 11.4 110 43 Jarnagin et al. 2006, ASHRAE 2007

Medium office (per floor) 9.9 37.5 110 43 Jarnagin et al. 2006, ASHRAE 2007

Large office (per floor) 21.3 80.6 110 43 Jarnagin et al. 2006, ASHRAE 2007

Apartment 3.5 13.2 110 43 Gowri et al. 2007

Outpatient healthcare 30.0 113.5 110 43 Doebber et al. 2009

Hospital

ER waiting room 1.0 3.8 120 49 Engineering judgment

Operating/surgical cystoscopic 2.0 7.6 120 49 Engineering judgment

Laboratory 2.0 7.6 120 49 Engineering judgment

Patient room 1.0 3.8 120 49 Engineering judgment

Data for the two hotel buildings are from Jiang et al. (2008) and ASHRAE (2007). Average hot 

water use per guest room is assumed to be 14 g/day (53 L/day) in the small hotel and 10 g/day 

(38 L/day) in the large hotel from Table 7 (ASHRAE 2007). These total daily consumption 

values are the product of the peak value and the SHW schedule, which assumes a total full load 

equivalent consumption over 8 hours per day and gives the hourly peak loads shown in Table 11. 
18

The laundry facility loads were modified from Jiang et al. (2008). We assumed 9 lb (4.1 kg) of 

laundry per room per day and 1.2 gal/lb (9.9 L/kg) of laundry of 140oF (60oC) hot water. The 

total hot water load for washing was divided evenly over 8 hours.

The average hot water use for schools is 0.6 gal/student/day (2.3 L/student/day) for primary 

schools and 1.8 gal/student/day (6.8 L/student/day) in secondary schools (ASHRAE 2007). We

assumed that the secondary school uses 0.6 gal/student/day (2.3 L/student/day) in the restrooms 

to match the use in the primary school and 1.2 gal/student/day (4.5 L/student/day) in the 

gymnasium showers. The primary school has 650 students and the secondary school has 1200 

students. The total daily hot water use was divided over the hot water use schedule to arrive at

the peak values shown in Table 11.

For the offices, we assumed 1 gal/occupant/day (3.8 L/occupant/day) divided evenly over a 9-h 

occupancy period. We assumed 310 gal/day (1,172 L/day) for the outpatient healthcare model 

over a 14-h occupancy period, with the operating rooms consuming the most SHW of all the 

space types. Healthcare space types consumed similar quantities of SHW in the hospital model, 

but most use occurred in the commercial kitchen associated with the hospital cafeteria.

5.1.7 Schedules

Few data are available that enable us to determine the best operating schedules for building 

energy simulations. We used the schedules from the AEDG Technical Support Documents for 

the schools, lodging, warehouse, and healthcare models and a PNNL study for the apartment 

model (see Table 12). For the other models we started with Standard 90.1-1989 Section 13, 

which includes schedules for use with the Energy Cost Budget Method (ASHRAE 1989). 

Schedules published in the original version of 90.1-1989 were modified by Addendum L in 1994 

by a public review process, and are published with minor modifications in Section G of the 

User’s Manual for 90.1-2004 (ASHRAE 2004c). Although these schedules are not perfect, no 

better published source of schedules has been identified. We started with these schedules and 

made modifications based on experience with monitoring real buildings to account for 

differences in zone-level and equipment operations, and lighting and plug loads. In 90.1-1989 

(with addenda), the lights and equipment share the same schedules, but case study research and 

broad anecdotal evidence suggest that plug and process loads do not track lighting loads and that 

during off hours the plug loads are higher, probably because of information technology and 

security equipment. Therefore, we created new plug and process schedules and developed

additional schedules for spaces that operate on different schedules, based on experience with 

monitoring buildings. All the schedules for each model are included in Appendix B.

Table 12 Reference Building Model Schedule Starting Points

Principal Building Activity Data Source

Office ASHRAE 1989

Education Pless et al. 2007

Retail ASHRAE 1989

Food Sales ASHRAE 1989

Food Services ASHRAE 1989

Lodging Jiang et al. 2008

Healthcare Doebber et al. 2009

Warehouse Liu et al. 2007

Apartment Gowri et al. 2007
19

5.1.8 Utility Tariffs

Utility rate schedules are needed to calculate energy costs, which are important for analyzing the 

economics of energy efficiency and energy production technologies. Electricity and natural gas 

are the only two energy forms considered for the reference buildings. Utility rate schedules vary 

widely across the country and within each census division, and capturing this variability is 

difficult. Also, utility rates can vary significantly from year to year. Utility rate schedules were 

selected from the EnergyPlus UtilityTariffObject.imf file when locations were selected. They

were taken from the Tariff Analysis Project (http://tariffs.lbl.gov/) and directly from the utility 

company Web sites. These data are from 2004 and may not reflect current prices. 

Tax rates on utilities vary at the city and county government levels, and most utility companies 

do not publish these with their tariffs because they vary within the service territory. However, 

taxes form an important part of energy costs in the commercial sector and should be included in 

the modeling. These data were filled by assuming that energy taxes are equal to the state sales 

tax rate plus 2% to cover city and county taxes based on a brief review of utility tax rates. 

5.2 Form

Building form parameters are listed in Table 3. The form parameters for each reference building 

are shown in Table 13. Aspect ratio is defined as the overall length in the east–west direction

divided by the overall length in the north–south direction. Expert opinion was used to determine 

the aspect ratios and floor-to-floor height for each building type. Ceiling plenums are included 

in the large office and medium office models. The sources for the other form parameters are 

shown in Table 14. 

Table 13 Reference Building Form Assignments

Building Type

Floor Area Aspect 

Ratio

No. of 

Floors

Floor-toFloor HeightFloor-toCeiling Height Glazing 

ft Fraction 2 m2 ft m ft m

Small Office 5,500 511 1.5 1 10 3.05 10 3.05 0.21

Medium Office 53,628 4,982 1.5 3 13 3.96 9 2.74 0.33

Large Office 498,588 46,320 1.5 12* 13 3.96 9 2.74 0.38

Primary School 73,960 6,871 E-Shape 1 13 3.96 13 3.96 0.35

Secondary School 210,887 19,592 E-Shape 2 13 3.96 13 3.96 0.33

Stand-Alone Retail 24,962 2,294 1.3 1 20 6.10 20 6.10 0.07

Strip Mall 22,500 2,090 4.0 1 17 5.18 17 5.18 0.11

Supermarket 45,000 4,181 1.5 1 20 6.10 20 6.10 0.11

Quick Service Restaurant 2,500 232 1.0 1 10 3.05 10 3.05 0.14

Full Service Restaurant 5,500 511 1.0 1 10 3.05 10 3.05 0.17

Small Hotel 43,200 4,013 3.0 4 11**

9

3.35**

2.74

11**

9

3.35**

2.74 0.11

Large Hotel 122,120 11,345 3.8**

5.1 6 13**10

3.96**

3.05

13**

10

3.96**

3.05 0.27

Hospital 241,351 22,422 1.3 5* 14 4.27 14 4.27 0.15

Outpatient Healthcare 40,946 3,804 1.4 3 10 3.05 10 3.05 0.19

Warehouse 52,045 4,835 2.2 1 28 8.53 28 8.53 0.006

Midrise Apartment 33,740 3,135 2.7 4 10 3.05 10 3.05 0.15

* Plus basement (not included in the table number)

** First floor
20

Table 14 Sources for Reference Building Form Data

Principal Building Activity Data Source

Small Office Jarnagin et al. 2006, EIA 2005

Medium Office EIA 2005

Large Office EIA 2005

Primary School Pless et al. 2007

Secondary School Pless et al. 2007

Stand-Alone Retail EIA 2005

Strip Mall EIA 2005

Supermarket EIA 2005

Quick Service Restaurant Huang et al. 1991

Full Service Restaurant Huang et al. 1991

Small Hotel Jiang et al. 2008

Large Hotel Huang et al. 1991

Hospital Huang et al. 1991

Outpatient Healthcare Doebber et al. 2009

Warehouse Liu et al. 2007

Midrise Apartment Gowri et al. 2007

5.3 Fabric

The fabric includes the construction types and thermal properties of the walls, roofs, floors, and 

windows. Winiarski et al. (2007a; 2007b) analyzed CBECS 2003 to determine pre-1980 and 

post-1980 construction types. They assumed that the new construction models and the post-1980

use the same construction types.

5.3.1 Envelope Constructions

CBECS PBAplus information was used to map data from the 2003 CBECS dataset to the 

reference building types. Office buildings were divided into small, medium, and large, based on 

the number of floors (small is defined as single story, medium as two to four stories, and large 

more than four stories). 

CBECS provides seven categories of roof construction material plus an “other” category and a 

“not one major type” category. The most common roof descriptions were determined for each 

reference building type by percentage of roof area and fraction of buildings. (No consideration is 

given to skylight area.) Roof area is assumed to correspond to the building footprint. This 

implies that roof area is equal to the projected roof area on the building footprint. No attempt

was made to estimate the relative increase in roof area for sloped roofs compared to flat roofs. 

Standard 90.1-2004 defines three primary roof types based on the location of insulation relative 

to the roof with the following assumptions: 
21

• Insulation Entirely Above Deck. Has continuous insulation above the structural roof 

deck.

• Metal Building. Has insulation compressed between structural members.

• Attic and Other. Insulation is laid between roof joists. 

A fourth option for determining roof insulation levels in Standard 90.1-2004 is defined as singlerafter roofs, a subclass of Attic and Other, in which the roof above and the ceiling below are 

attached to the same rafter. For these assemblies, the requirement in Standard 90.1-2004 is the 

lesser of two values: the attic requirement or a separate requirement that the rafter cavity be 

filled with fiberglass insulation. We consider single-rafter roofs in the Attic and Other 

classification; no further consideration is given to single-rafter roofs. 

Comparison of the three ASHRAE Standard 90.1-2004 roof types with the 2003 CBECS roof 

descriptions indicates that the only description that can be unambiguously mapped to a Standard 

90.1 roof type is the CBECS built-up classification mapped to 90.1 Insulation Entirely Above 

Deck. Slate, shingles, shakes, and tiles of any material map fairly well to the Standard 90.1 Attic 

and Other category, as these are typically installed over an attic or single-rafter roof. Less 

straightforward is mapping the CBECS Asphalt, Fiberglass, Other classification. This category 

can be mapped to 90.1’s Attic and Other in the case of asphalt shingles, but could also be 

mapped to Insulation Entirely Above Deck in the case of a built-up roof with an asphalt topcoat. 

The CBECS Metal Surface category may be mapped to 90.1 Metal Building, or it may indicate 

that a metal roof has been used in place of shingles over an attic roof structure. The CBECS 

Plastic, Rubber, Synthetic category most likely maps to the Insulation Entirely Above Deck 

category (most commonly where a synthetic membrane is placed over foam), although 

commercially available recycled rubber and plastic shingles could be installed over an attic. 

These relationships are shown in Table 15. 

Table 15 Relationship of CBECS Roof Descriptions and Standard 90.1 Roof Constructions

CBECS Roof Descriptions

Standard 90.1 Roof Construction

Insulation Entirely 

Above Deck Metal Building Attic and Other

Asphalt, fiberglass, other X X

Built-up X

Concrete X

Metal surfacing X X

No one major type

Other

Plastic, rubber, synthetic X X

Slate, tile shingles X

Wood shingles, shakes, other X

CBECS provides the Wall Construction (WLCNS) statistic as a classification of the major wall 

construction type for each building. The CBECS WLCNS categories are:

• Brick, stone, or stucco

• Concrete block or poured concrete

• Decorative or construction glass
22

• Precast concrete panels

• Sheet metal panels

• Siding, shingles, tiles, or shakes

• Window or vision glass 

• No one major type 

• Other. 

For each reference building, Table 16 lists the top five CBECS WLCNS choices in decreasing 

order of occurrence by percentage of calculated total opaque wall area or number of buildings. 

To determine the percentage of total opaque wall area, we removed the window area from the 

frequency statistic (total wall area). Some buildings have their primary wall construction in 

CBECS characterized as vision or construction glass, which is not opaque. Thus, these buildings 

tend to rank lower than if we had ranked buildings by total wall area including glazed area.

Table 16 Relationships Between CBECS Wall Descriptions and Standard 90.1 Wall Constructions

CBECS Wall Descriptions

ASHRAE Standard 90.1 Wall Construction

Mass Wall

Metal Building 

Wall

Steel Framed 

Wall

Wood Framed 

and Other Wall

Brick, stone, stucco X X X X

Concrete, block or poured X

Precast concrete panels X

Sheet metal panels X

Siding, shingles, tiles, shakes X X

Decorative or construction glass X

Window or vision glass X

No major type Unknown Unknown Unknown Unknown

Other Unknown Unknown Unknown Unknown

Standard 90.1-2004 defines four wall types based on the functional performance of the wall, with 

the following assumptions: 

• Mass Wall. Has continuous insulation.

• Metal Building Wall. Has insulation compressed between metal members, possibly 

augmented by continuous insulation to decrease the overall U-factor. 

• Steel Framed Wall. Is a simple frame wall with different structural members (and 

therefore different thermal bypass factors). 

• Wood Framed and Other Wall. Is a simple frame wall with different structural 

members (and therefore different thermal bypass factors). 

Mass Wall in Standard 90.1-2004 must be defined as a wall with a heat capacity exceeding

7 Btu/ft2

·°F (143 MJ/m2·°C) or 5 Btu/ft2·°F (102 MJ/m2·°C), provided that it has a material unit 

weight not greater than 120 lb/ft3 (4.7 GJ/m3). The 7 Btu/ft2·°F is for any weight wall; the

5 Btu/ft2· ̊F (102 MJ/m2·°C) is only for walls lighter than 120 lb/ft3 (4.7 GJ/m3). Thus, regardless 

of insulation type and placement, walls exceeding this level of heat capacity are treated as mass 

walls for setting minimum U-factor requirements. The definition is such that a 4-in. (10-cm) 

brick facing on a frame wall construction does not create a mass wall under the Standard 90.1 

definition.
23

Comparing the four Standard 90.1-2004 wall types with the 2003 CBECS wall descriptions 

indicates that the brick, stone, and stucco description could conceivably be mapped to any one of 

the four ASHRAE 90.1 WLCNSs. This is problematic because the brick, stone, and stucco 

description is the single most common in the 2003 CBECS for all the reference building types 

examined in this analysis. These relationships between the Standard 90.1-2004 roof types and 

the 2003 CBECS wall descriptions are shown in Table 16. 

The recommended roof and wall constructions for each model and each construction vintage are 

shown in Table 17 and Table 18. Winiarski et al. (2006) recommended an attic roof construction 

for the new construction small hotel; however, Jiang et al. (2008) recommended insulation 

entirely above deck for the roof, which is used in the reference small hotel model. Gowri et al. 

(2007) determined the constructions for the midrise apartment building model and assumed they 

were the same for all vintages of the reference building. 

Table 17 Recommended Roof Constructions by Building Type

Building Type Pre-1980 Post-1980 New Construction

Small Office Insulation entirely 

above deck Attic and other Attic and other

Medium Office Insulation entirely 

above deck

Insulation entirely 

above deck

Insulation entirely 

above deck

Large Office Insulation entirely 

above deck

Insulation entirely 

above deck

Insulation entirely 

above deck

Primary School Insulation entirely 

above deck

Insulation entirely 

above deck

Insulation entirely 

above deck

Secondary School Insulation entirely 

above deck

Insulation entirely 

above deck

Insulation entirely 

above deck

Stand-Alone Retail Insulation entirely 

above deck

Insulation entirely 

above deck

Insulation entirely 

above deck

Strip Mall Insulation entirely 

above deck

Insulation entirely 

above deck

Insulation entirely 

above deck

Supermarket Insulation entirely 

above deck

Insulation entirely 

above deck

Insulation entirely 

above deck

Quick Service Restaurant Insulation entirely 

above deck Attic and other Attic and other

Full Service Restaurant Insulation entirely 

above deck Attic and other Attic and other

Small Hotel Attic and other Attic and other Insulation entirely 

above deck

Large Hotel Insulation entirely 

above deck

Insulation entirely 

above deck

Insulation entirely 

above deck

Hospital Insulation entirely 

above deck

Insulation entirely 

above deck

Insulation entirely 

above deck

Outpatient Healthcare Insulation entirely 

above deck

Insulation entirely 

above deck

Insulation entirely 

above deck

Warehouse Insulation entirely 

above deck Metal building roof Metal building roof

Midrise Apartment Insulation entirely 

above deck

Insulation entirely 

above deck

Insulation entirely 

above deck
24

Table 18 Recommended Wall Constructions by Building Type

Building Type Pre-1980 Post-1980 New Construction

Small Office Steel frame Mass Mass

Medium Office Steel frame Steel frame Steel frame

Large Office Mass Mass Mass

Primary School Steel frame Steel frame Steel frame

Secondary School Steel frame Steel frame Steel frame

Stand-Alone Retail Steel frame Mass Mass

Strip Mall Steel frame Steel frame Steel frame

Supermarket Mass Mass Mass

Quick Service Restaurant Mass Wood frame Wood frame

Full Service Restaurant Steel frame Steel frame Steel frame

Small Hotel Steel frame Steel frame Steel frame

Large Hotel Mass Mass Mass

Hospital Mass Mass Mass

Outpatient Healthcare Steel frame Steel frame Steel frame

Warehouse Metal building Metal building Metal building

Midrise Apartment Steel frame Steel frame Steel frame

The choice of a wall or roof type for a reference building has energy implications. Versions of 

ASHRAE Standard 90 (dating back to 90-75) have different assembly U-factor requirements for 

different wall and roof types. For example, Standard 90.1-2004 has a variation for roof assembly 

U-factor of 0.034 to 0.065 (depending on roof type) in Zone 5 (typical of Chicago, Illinois). This 

same building in the same location could show a variation in wall assembly U-factor of 0.084 

to 0.113 for lightweight construction. 

The overall U-values of opaque constructions and fenestrations must be determined for the 

different vintages of baseline building models. The new construction reference building models 

follow Standard 90.1-2004; the post-1980 models follow Standard 90.1-1989. For the pre-1980 

models, we chose to follow values from Briggs et al. (1987), who estimated envelope thermal 

properties by construction year for office buildings. We estimated the envelope thermal 

properties from the Briggs paper for 1970 construction and assumed that these values apply 

across all building and construction types. Table 19 through Table 25 show the roof and wall Uvalues, slab-on-grade and underground R-values, window U-values, and solar heat gain 

coefficients (SHGCs) for all construction types and for the three vintages of reference buildings. 

The U-values include the interior and exterior film coefficients from Standard 90.1-2004.

Standard 90.1-2004 contains residential and nonresidential construction performance parameters. 

The residential constructions are more stringent and should be used for whole buildings or floors

of buildings where 50% or more of the spaces adjacent to the exterior walls are used primarily 

for living and sleeping quarters. This definition requires that the residential constructions be 

used for the small hotel and midrise apartment, for floors 2–4 of the hospital, and for floors 2–6 

of the large hotel. 
25

Table 19 Roof U-Values (Btu/h·ft2·oF) by Reference Building Vintage

Location

90.1-2004

Climate 

Zone

90.1-1989 

Table

Pre1980Post1980

New Construction 

Insulation 

Above Deck

New 

Construction 

Attic

Miami, FL 1A 8A-15 0.100 0.074 0.063 0.034

Houston, TX 2A 8A-10 0.100 0.066 0.063 0.034

Phoenix, AZ 2B 8A-18 0.100 0.046 0.063 0.034

Atlanta, GA 3A 8A-8 0.100 0.072 0.063 0.034

Los Angeles, CA 3B-CA 8A-6 0.100 0.100 0.063 0.034

Las Vegas, NV 3B-other 8A-14 0.100 0.048 0.063 0.034

San Francisco, CA 3C 8A-5 0.100 0.088 0.063 0.034

Baltimore, MD 4A 8A-25 0.086 0.058 0.063 0.034

Albuquerque, NM 4B 8A-23 0.089 0.059 0.063 0.034

Seattle, WA 4C 8A-19 0.085 0.064 0.063 0.034

Chicago, IL 5A 8A-26 0.072 0.053 0.063 0.034

Denver, CO 5B 8A-28 0.076 0.051 0.063 0.034

Minneapolis, MN 6A 8A-33 0.060 0.045 0.063 0.027

Helena, MT 6B 8A-32 0.060 0.049 0.063 0.027

Duluth, MN 7 8A-36 0.060 0.040 0.063 0.027

Fairbanks, AK 8 8A-38 0.060 0.031 0.048 0.027

Table 20 Steel Frame Wall U-Values (Btu/h·ft2·oF) by Reference Building Vintage

Location

90.1-2004

Climate 

Zone

90.1-1989 

Table

Pre-1980 Post-1980 New Construction

Btu/

h·ft2·oF W/m2·K

Btu/

h·ft2·oF W/m2·K

Btu/

h·ft2·oF W/m2·K

Miami, FL 1A 8A-15 0.230 1.306 1.000 5.678 0.124 0.704

Houston, TX 2A 8A-10 0.230 1.306 0.150 0.852 0.124 0.704

Phoenix, AZ 2B 8A-18 0.230 1.306 0.240 1.363 0.124 0.704

Atlanta, GA 3A 8A-8 0.225 1.278 0.130 0.738 0.124 0.704

Los Angeles, CA 3B-CA 8A-6 0.230 1.306 0.220 1.249 0.124 0.704

Las Vegas NV 3B-other 8A-14 0.230 1.306 0.160 0.909 0.124 0.704

San Francisco, CA 3C 8A-5 0.224 1.272 0.130 0.738 0.124 0.704

Baltimore, MD 4A 8A-25 0.178 1.011 0.089 0.505 0.124 0.704

Albuquerque, NM 4B 8A-23 0.184 1.045 0.100 0.568 0.124 0.704

Seattle, WA 4C 8A-19 0.175 0.994 0.092 0.522 0.124 0.704

Chicago, IL 5A 8A-26 0.156 0.886 0.082 0.466 0.084 0.477

Denver, CO 5B 8A-28 0.161 0.914 0.082 0.466 0.084 0.477

Minneapolis, MN 6A 8A-33 0.145 0.823 0.065 0.369 0.084 0.477

Helena, MT 6B 8A-32 0.145 0.823 0.072 0.409 0.084 0.477

Duluth, MN 7 8A-36 0.136 0.772 0.058 0.329 0.064 0.363

Fairbanks, AK 8 8A-38 0.125 0.710 0.045 0.256 0.064 0.363
26

Table 21 Mass Wall U-Values (Btu/h·ft2·oF) by Reference Building Vintage

Location

90.1-2004

Climate 

Zone

90.1-1989 

Table

Pre-1980 Post-1980 New Construction

Btu/

h·ft2·oF W/m2·K

Btu/

h·ft2·oF W/m2·K

Btu/

h·ft2·oF W/m2·K

Miami, FL 1A 8A-15 0.230 1.306 1.000 5.678 0.580 3.293

Houston, TX 2A 8A-10 0.230 1.306 0.340 1.931 0.580 3.293

Phoenix, AZ 2B 8A-18 0.230 1.306 0.410 2.328 0.580 3.293

Atlanta, GA 3A 8A-8 0.225 1.278 0.290 1.647 0.151 0.857

Los Angeles, CA 3B-CA 8A-6 0.230 1.306 1.000 5.678 0.151 0.857

Las Vegas, NV 3B-other 8A-14 0.230 1.306 0.290 1.647 0.580 3.293

San Francisco, CA 3C 8A-5 0.224 1.272 0.490 2.782 0.580 3.293

Baltimore, MD 4A 8A-25 0.178 1.011 0.120 0.681 0.580 3.293

Albuquerque, NM 4B 8A-23 0.184 1.045 0.190 1.079 0.151 0.857

Seattle, WA 4C 8A-19 0.175 0.994 0.100 0.568 0.151 0.857

Chicago, IL 5A 8A-26 0.156 0.886 0.100 0.568 0.151 0.857

Denver, CO 5B 8A-28 0.161 0.914 0.140 0.795 0.151 0.857

Minneapolis, MN 6A 8A-33 0.145 0.823 0.071 0.403 0.123 0.698

Helena, MT 6B 8A-32 0.145 0.823 0.079 0.449 0.123 0.698

Duluth, MN 7 8A-36 0.136 0.772 0.061 0.346 0.123 0.698

Fairbanks, AK 8 8A-38 0.125 0.710 0.047 0.267 0.104 0.591

Table 22 Unheated Slab-On-Grade Floor Insulation by Reference Building Vintage R-Value 

(h·ft2

·oF/Btu) for 24-in. Vertical Insulation

Location

90.1-2004

Climate Zone

90.1-1989 

Table Pre-1980 Post-1980

New 

Construction

Miami, FL 1A 8A-15 0.0 0.0 NR

Houston, TX 2A 8A-10 0.0 0.0 NR

Phoenix, AZ 2B 8A-18 0.0 0.0 NR

Atlanta, GA 3A 8A-8 0.0 6.0 NR

Los Angeles, CA 3B-CA 8A-6 0.0 0.0 NR

Las Vegas, NV 3B-other 8A-14 0.0 0.0 NR

San Francisco, CA 3C 8A-5 0.0 6.0 NR

Baltimore, MD 4A 8A-25 0.0 8.0 NR

Albuquerque, NM 4B 8A-23 0.0 7.0 NR

Seattle, WA 4C 8A-19 0.0 8.0 NR

Chicago, IL 5A 8A-26 0.0 8.0 NR

Denver, CO 5B 8A-28 0.0 8.0 NR

Minneapolis, MN 6A 8A-33 0.0 8.0 NR

Helena, MT 6B 8A-32 0.0 8.0 NR

Duluth, MN 7 8A-36 0.0 8.0 NR

Fairbanks, AK 8 8A-38 0.0 8.0 10.0
27

Table 23 Underground Wall Insulation by Reference Building Vintage R-Value (h·ft2·oF/Btu)

Location

90.1-2004

Climate Zone

90.1-1989 

Table Pre-1980 Post-1980

New 

Construction

Miami, FL 1A 8A-15 0.0 0.0 NR

Houston, TX 2A 8A-10 0.0 0.0 NR

Phoenix, AZ 2B 8A-18 0.0 0.0 NR

Atlanta, GA 3A 8A-8 0.0 7.0 NR

Los Angeles, CA 3B-CA 8A-6 0.0 0.0 NR

Las Vegas, NV 3B-other 8A-14 0.0 0.0 NR

San Francisco, CA 3C 8A-5 0.0 7.0 NR

Baltimore, MD 4A 8A-25 0.0 9.0 NR

Albuquerque, NM 4B 8A-23 0.0 8.0 NR

Seattle, WA 4C 8A-19 0.0 9.0 NR

Chicago, IL 5A 8A-26 0.0 10.0 NR

Denver, CO 5B 8A-28 0.0 10.0 NR

Minneapolis, MN 6A 8A-33 0.0 12.0 NR

Helena, MT 6B 8A-32 0.0 11.0 NR

Duluth, MN 7 8A-36 0.0 13.0 7.5

Fairbanks, AK 8 8A-38 0.0 16.0 7.5

Table 24 Window Overall U-Value (Btu/h·ft2·oF) by Reference Building Vintage

Location

90.1-2004

Climate Zone

90.1-1989 

Table Pre-1980 Post-1980

New 

Construction

Miami, FL 1A 8A-15 1.22 1.22 1.22

Houston, TX 2A 8A-10 1.22 1.22 1.22

Phoenix, AZ 2B 8A-18 1.22 1.22 1.22

Atlanta, GA 3A 8A-8 1.22 0.72 0.57

Los Angeles, CA 3B-CA 8A-6 1.22 1.22 0.57

Las Vegas, NV 3B-other 8A-14 1.22 1.22 0.57

San Francisco, CA 3C 8A-5 1.22 0.72 1.22

Baltimore, MD 4A 8A-25 1.22 0.59 0.57

Albuquerque, NM 4B 8A-23 1.22 0.72 0.57

Seattle, WA 4C 8A-19 1.22 0.72 0.57

Chicago, IL 5A 8A-26 0.62 0.59 0.57

Denver, CO 5B 8A-28 0.62 0.59 0.57

Minneapolis, MN 6A 8A-33 0.62 0.52 0.57

Helena, MT 6B 8A-32 0.62 0.52 0.57

Duluth, MN 7 8A-36 0.62 0.52 0.57

Fairbanks, AK 8 8A-38 0.62 0.52 0.35
28

Table 25 Window Solar Heat Gain Coefficient by Reference Building Vintage

Location

90.1-2004

Climate Zone

90.1-1989 

Table Pre-1980 Post-1980

New 

Construction

Miami, FL 1A 8A-15 0.54 0.25 0.25

Houston, TX 2A 8A-10 0.54 0.25 0.25

Phoenix, AZ 2B 8A-18 0.54 0.25 0.25

Atlanta, GA 3A 8A-8 0.54 0.25 0.25

Los Angeles, CA 3B-CA 8A-6 0.54 0.44 0.25

Las Vegas, NV 3B-other 8A-14 0.54 0.25 0.25

San Francisco, CA 3C 8A-5 0.54 0.39 0.34

Baltimore, MD 4A 8A-25 0.54 0.36 0.39

Albuquerque, NM 4B 8A-23 0.54 0.36 0.39

Seattle, WA 4C 8A-19 0.54 0.39 0.39

Chicago, IL 5A 8A-26 0.41 0.39 0.39

Denver, CO 5B 8A-28 0.41 0.39 0.39

Minneapolis, MN 6A 8A-33 0.41 0.39 0.39

Helena, MT 6B 8A-32 0.41 0.39 0.39

Duluth, MN 7 8A-36 0.41 0.49 0.49

Fairbanks, AK 8 8A-38 0.41 NR NR

Standard 90.1-2004 has different roof U-values depending on the construction type; the U-value 

for Attic and Other is typically about half that for Insulation Entirely Above Deck. Standard 

90.1-1989 has only one value for the roof U-value, and the Briggs paper does not differentiate by 

construction type. Therefore, we use the same roof U-value for all construction types in the pre1980 and post-1980 constructions. 

Standard 90.1-1989 has varying levels of insulation for mass walls, depending on the internal 

load density (ILD), the wall heat capacity, the amount of fenestration, and the location of the 

insulation. We made the following assumptions:

• The ILD for all building types is 1.5–3 W/ft2.

• The heat capacity of the walls is greater than 15 Btu/ft2·oF.

• The percent fenestration is in the lower of the two ranges.

• The insulation is on the interior of the mass wall.

Briggs et al. (1987) published wall U-values for mass walls only. Thus, we used the same value 

for the pre-1980 steel frame wall construction. This paper does not include underground walls, 

and we assumed that there is no insulation on pre-1980 underground walls for all locations.

Standard 90.1-1989 contains ranges of window U-values and shading coefficients, depending on 

the window-to-wall glazing fraction and ILD. We assumed the highest U-values from 90.1-1989 

for the post-1980 reference buildings, which agree very closely with other versions of Standard 

90.1 for most locations. We used the SHGC from Standard 90.1-1999 for the post-1980 

reference buildings. For the pre-1980 reference buildings, we assumed the windows in climate 

zones 1–4 are single glazed 0.25-in. (.6-cm) bronze tinted glass and for climate zones 5–8, 

double-glazed bronze and clear glass windows. For new construction following 90.1-2004, we 
29

assumed all windows are fixed except the midrise apartment building, which is assumed to have 

operable windows.

5.3.2 Infiltration

Infiltration is different in each building and varies continuously with changing environmental 

and building operating conditions. Modeling approaches to infiltration are typically very simple 

because of the lack of knowledge about the sizes and distribution of cracks in the building 

envelope, the permeability of the envelope, the flow of air internal to the building, and the 

pressure distribution in and around the building. EnergyPlus allows a simple approach and a 

more detailed air flow nodal network approach to infiltration modeling. We chose the simple

approach to simplify the assumptions needed and to decrease simulation run times. 

The simple method has an empirical correlation that modifies the infiltration as a function of 

wind speed and temperature difference across the envelope. The difficulty in using this equation 

is determining valid coefficients for each building type in each location. The EnergyPlus 

documentation presents two sets of correlation coefficients, both of which were derived from a 

small number of measurements taken from published reports. These coefficients vary 

dramatically and provide very different results that cause great uncertainty in determining which 

numbers to use. Therefore, we chose to model a fixed infiltration rate (which may not be 

realistic for hourly modeling), but we feel that it can represent the average impact over a year.

Even in the simple model, we have to make assumptions about the infiltration level and how it is 

affected by the operation of the mechanical ventilation systems. A proposed addendum to 

Standard 90.1-2004 included an airtightness level for building envelopes. This document 

proposed that one approach to meeting the standard would be to perform a pressurization test to 

show that the building leakage does not exceed 0.4 cfm/ft2 at 0.3 in. w.c. (2 L/s/m2 at 75 Pa) of 

above-grade envelope area (exterior walls and roof). This airtightness level provides a number 

that can be used for the energy simulations and was assumed to be the level for new construction 

reference building models. 

For existing buildings, we turn to measured airtightness data. Persily (1998) collected data from 

139 buildings that showed a wide scatter in airtightness and little correlation between building

age and airtightness. The average leakage rate across all building types and locations was 1.5 

cfm/ft2 at 0.3 in. w.c. (7.5 L/s/m2 at 75 Pa) of above-grade envelope area. This number is used 

for the pre-1980 and post-1980 reference building models.

Several assumptions have to be made to go from leakage rates to the simple infiltration model in 

the building energy simulation. The infiltration was calculated based on the above-grade 

envelope area (exterior walls and roof), then converted to a pressure of 0.016 in. w.c. (4 Pa),

assuming a flow exponent of 0.65. This lower pressure was assumed to be the average pressure 

difference across the envelope without pressurization or depressurization from the HVAC and 

exhaust fans. 

Infiltration is often assumed to drop to zero when buildings are pressurized in energy models,

because there is a lack of evidence about what really happens and lack of knowledge about how 

to model it in an energy simulation. We assumed that the uncontrolled infiltration is reduced to 

25% of the value calculated at 0.016 in. w.c. (4 Pa) when the ventilation system is running. 

When the ventilation system is off (no OA), the infiltration is modeled at the full leakage rate 

calculated at 0.016 in. w.c. (4 Pa). Infiltration is modeled at constant air changes per hour
30

(ACH). We assumed that constant ACH models the average effects over the year and in 

different locations. This is a gross simplification, but is necessary without moving to more 

complicated flow network simulations. 

5.4 Equipment

The equipment category includes interior and exterior lighting, HVAC, SWH equipment, and 

commercial refrigeration systems. 

5.4.1 Interior Lighting

We used the building area method or the space-by-space method from Standard 90.1-2004 to 

determine maximum lighting power densities (LPDs) for the new construction models and 

Standard 90.1-1989 for the existing building models (see Table 26). For space types not defined 

in Standard 90.1-2004 for the hospital and outpatient models, we took LPD values from GGHC 

(2007). The LPDs for each zone in each building are listed in Appendix A.

The LPDs in the strip mall were divided into three levels: high in two stores, medium in three 

stores, and low in five stores to simulate a mix of stores based on research from Liu et al. (2006). 

We assumed that the typical pre-1980 building lighting systems were updated to at least the 

Standard 90.1-1989 LPDs. Standard 90.1-1989 provides prescriptive criteria and system 

performance criteria approaches for determining the allowed lighting power. The prescriptive 

criteria approach provides building-level LPDs. The system performance criteria approach 

provides space-level LPDs and an area factor (AF) multiplier. The LPD for reference buildings

with multiple space types was determined as the product of the allowable unit power density

from ASHRAE (1989). The AF is defined as

( ) n AF = 0.2 + 0.8 1 0.9

( ) 1

A

10.21 CH 2.5

n

r

− − =

where

AF = area factor

Ar = room area, ft2

CH = ceiling height, ft
31

Table 26 Reference Building Lighting Assumptions

Building Type

Existing Stock Models 

(ASHRAE 90.1-1989)

New Construction Models 

(ASHRAE 90.1-2004)

Small Office Table 6-5 Offices Table 9.5.1 office 

Medium Office Table 6-5 Offices Table 9.5.1 office 

Large Office Table 6-5 Offices Table 9.5.1 office 

Primary School Table 6-6a by space type 

(classroom AF = 1.0) Table 9.6.1 by space type

Secondary School Table 6-6a by space type 

(classroom AF = 1.0) Table 9.6.1 by space type

Stand-Alone Retail Table 6-6b retail space type C; 

Table 6-6a fine storage for back

Table 9.6.1 sales area, active 

storage

Strip Mall 

2 Stores: 5.6 W/ft2 (60.26 W/m2) 

(Table 6-6b space type A)

3 Stores: 3.3 W/ft2 (35.51 W/m2) 

(Table 6-6b space type C) 

5 Stores: 2.7W/ft2 (29.05 W/m2) 

(Table 6-6b space type F)

2 Stores: 2.23 W/ft2 (24 W/m2) 

(Table 9.6.1 retail plus accent 

lighting)

3 Stores: 1.7 W/ft2 (18.3 W/m2) 

(Table 9.6.1 retail) 

5 Stores: 1.28 W/ft2 (13.8 W/m2)

Supermarket

Table 6-6b retail space type E; 

Table 6-6a office category 1; 

Table 6-6a fine storage for back

Table 9.6.1 sales area, active 

storage 

Quick Service Restaurant Table 6-6a by space type Table 9.6.1 family dining; food prep

Full Service Restaurant Table 6-6a by space type Table 9.6.1 family dining; food prep

Small Hotel Table 6-6b by space type Table 9.6.1 by space type

Large Hotel Table 6-6b by space type Table 9.6.1 by space type

Hospital Table 6-6b by space type Table 9.6.1 by space type

Outpatient Healthcare

Table 6-5 offices and 

Table 6.6b dental suite/

examination

Table 9.6.1 by space type

GGHC 2007

Table L-1 where appropriate

Warehouse Table 6-6a by space type Table 9.6.1 office, bulk storage, 

fine storage

Midrise Apartment Hendron 2007, 90.1-1989

Table 6-6a for corridor

Hendron 2007, 90.1-2004

Table 9.6.1 for corridor

5.4.2 Exterior Lights

Exterior lighting is included in all reference building models following the values shown in 

Table 27 and Table 28. All exterior lighting operates on an astronomical clock that turns on the 

lights when the sun is down and turns them off when the sun is up. Exterior façade lighting is 

included in all buildings around the perimeter of the building per area of the first floor exterior 

walls plus the first floor plenum exterior walls. Exterior lights were added to the main entryway 

doors and other exterior doors in all models. Exterior canopy lights were included in the small 

hotel, large hotel, and hospital emergency room entrances. The hotel canopies are considered to 

be high traffic areas and the hospital emergency room entrance is considered to be a low traffic 
32

area for Standard 90.1-1989. The quick service restaurant model includes lighting for the drivethrough window. Standard 90.1-1989 does not have a category for drive-through windows; 

therefore, we used the Standard 90.1-2004 value for the existing stock models.

Table 27 Exterior Lighting Assumptions

Area

Existing Stock Models 

(90.1-1989)

New Construction Models 

(90.1-2004)

Façade 0.25 W/ft2 (2.69 W/m2

) 0.2 W/ft2 (2.15 W/m2)

Main entry doors 30 W/ft (98.4 W/m) 30 W/ft (98.4 W/m)

Other doors 25 W/ft (82.0 W/m) 20 W/ft (65.6 W/m)

Canopy (heavy traffic) 10 W/ft2 (108 W/m2

) 1.25 W/ft2 (13.5 W/m2)

Canopy (light traffic) 4 W/ft2 (43 W/m2

) 1.25 W/ft2 (13.5 W/m2)

Drive through – 400 W

Parking lot 0.18 W/ft2 (1.9 W/m2

) 0.15 W/ft2 (1.6 W/m2)

Table 28 Parking Lot Lighting Levels

Building Type Parking Lot Area

Total Parking Lot Lighting Level

Existing Stock 

Models

New Construction 

Models

Small Office 8,910 ft2 (828 m2

) 1,604 W 1,337 W

Medium Office 86,832 ft2 (8,067 m2

) 15,630 W 13,025 W

Large Office 325,087 ft2 (30,201 m2

) 58,516 W 48,763 W

Primary School 14,718 ft2 (1,367 m2

) 2,649 W 2,208 W

Secondary School 59,263 ft2 (5,506 m2

) 10,667 W 8,889 W

Stand-Alone Retail 35,018 ft2 (3,253 m2

) 6,303 W 5,253 W

Strip Mall 42,368 ft2 (3,936 m2

) 7,626 W 6,355 W

Supermarket 63,810 ft2 (5,928 m2

) 11,486 W 9,572 W

Quick Service Restaurant 10,125 ft2 (941 m2

) 1,823 W 1,519 W

Full Service Restaurant 22,275 ft2 (2,069 m2

) 4,010 W 3,341 W

Small Hotel 33,696 ft2 (3,130 m2

) 6,065 W 5,054 W

Large Hotel 88,544 ft2 (8,226 m2

) 15,938 W 13,282 W

Hospital 77,493 ft2 (7,199 m2

) 13,949 W 11,624 W

Outpatient Healthcare 82,924 ft2 (7,704 m2

) 14,926 W 12,439 W

Warehouse 20,048 ft2 (1,862 m2

) 3,609 W 3,007 W

Midrise Apartment 28,578 ft2 (2,655 m2

) 5,144 W 4,287 W

5.4.3 HVAC Equipment

ASHRAE (2004) specifies HVAC equipment for baseline buildings. This information is used to

develop reference buildings and does not necessarily represent typical construction practices. 

Winiarski et al. (2006) performed an analysis of 2003 CBECS to estimate typical HVAC system 

types by building type to use with the reference buildings. They examined the data in two sets: 
33

all buildings with a construction year of 1980 or earlier and the remaining buildings built after 

1980. The final equipment types selected represented the largest percentage of floor area. The 

results for post-1980 and new construction are shown in Table 29 and for pre-1980 construction 

in Table 30. Strip malls were not included and are assumed to have the same systems as the 

stand-alone retail model. The number of chillers and condenser type (air or water) were

determined by discussions with the ASHRAE Standard 90.1 mechanical subcommittee.

Table 29 HVAC Equipment Types for Post-1980 and New Construction 

Building Type Heating Cooling Air Distribution

Small Office Furnace PACU (packaged airconditioning unit)

SZ CAV (single-zone 

constant air volume)

Medium Office Furnace PACU MZ VAV (multizone 

variable air volume)

Large Office Boiler Chiller (2) – water 

cooled MZ VAV

Primary School Boiler PACU CAV

Secondary School Boiler Chiller – air cooled MZ VAV

Stand-Alone Retail Furnace PACU SZ CAV

Strip Mall Furnace PACU SZ CAV

Supermarket Furnace PACU CAV

Quick Service Restaurant Furnace PACU SZ CAV

Full Service Restaurant Furnace PACU SZ CAV

Small Hotel

ISH (individual 

space heater), 

furnace

IRAC (individual room 

air conditioner), PACU SZ CAV

Large Hotel Boiler Chiller (2) – air cooled FCU (fan coil unit) 

and VAV*

Hospital Boiler Chiller – water cooled CAV and VAV**

Outpatient Healthcare Furnace PACU CAV and VAV**

Warehouse ISH, furnace PACU SZ CAV

Midrise Apartment Furnace PACU-SS (split system) SZ CAV

* Hotels may be characterized with two system types serving different areas. Both multizone systems (VAV or 

CAV) may serve public spaces (lobby/conference rooms), whereas single zone fan coil systems may be common 

for living areas. 

** Hospitals may use CAV systems in some operating and critical care type areas with variable air flow used for 

pressurization, but classic VAV multizone systems in areas such as offices. CBECS buildings reporting VAV are 

significantly less common in pre-1980 construction (67% versus 95% in post-1980 hospitals).
34

Table 30 HVAC Equipment Types for Pre-1980 Construction 

Building Type Heating Cooling Air Distribution

Small Office Furnace PACU SZ CAV

Medium Office Furnace PACU SZ CAV

Large Office Boiler Chiller (2) – water cooled MZ VAV

Primary School Boiler PACU CAV

Secondary School Boiler PACU CAV

Stand-Alone Retail Furnace PACU SZ CAV

Strip Mall Furnace PACU SZ CAV

Supermarket Furnace PACU CAV

Quick Service Restaurant Furnace PACU SZ CAV

Full Service Restaurant Furnace PACU SZ CAV

Small Hotel ISH IRAC SZ CAV

Large Hotel Boiler Chiller (2) – air cooled FCU and MZ CAV*

Hospital Boiler Chiller – water cooled FCU, CAV and VAV**

Outpatient Healthcare Furnace PACU CAV and VAV**

Warehouse Furnace, ISH PACU SZ CAV

Midrise Apartment Furnace PACU-SS SZ CAV

* Hotels may be characterized with two system types serving different areas. Both multizone systems (VAV or 

CAV) may serve public spaces (lobby/conference rooms), whereas single zone fan coil systems may be common 

for living areas. 

** Hospitals may use CAV systems in some operating and critical care type areas with variable air flow used for 

pressurization, but classic VAV multizone systems in areas such as offices. CBECS buildings reporting VAV are 

significantly less common in pre-1980 construction (67% versus 95% in post-1980 hospitals).

Equipment sizing for all reference building models is determined from design day runs by 

EnergyPlus for each location with a sizing factor of 1.2. Nominal coefficient of performance 

(COP), energy efficiency ratio (EER), seasonal energy efficiency ratio (SEER), and boiler and 

furnace efficiencies are taken from the appropriate energy standard based on equipment type and 

size. Performance curves and HVAC system models are used to model how performance might 

vary when operating away from the nominal operation point using the models available in 

EnergyPlus. Economizer operation is determined from the cooling system size and climate zone 

following 90.1-2004 requirements. Exception (e) to Section 6.5.1 in 90.1-2004 for systems 

serving residential spaces eliminates the requirement for economizers for systems smaller than 

27 tons and 56 tons, depending on climate zone. Moreover, economizers are not used in any 

healthcare critical systems that are required to operate within specified humidity constraints.

The equipment efficiencies are determined from 90.1-2004 for the new construction reference

building models, 90.1-1989 for the post-1980 reference building models, and from an analysis of 

historical equipment efficiencies and equipment lifetimes for the pre-1980 reference building 

models (Winiarski and Halverson 2008). The equipment efficiencies for pre-1980 reference

building models for cooling equipment are shown in Table 31, for space heating equipment in

Table 32, and for water heating equipment in Table 33 through Table 35.
35

Table 31 Estimated Unitary Cooling Equipment Efficiencies for Pre-1980 Construction

Equipment Category Capacity

(Btu/h) Heating Section Equipment Subcategory Efficiency Metric

Average 

Efficiency

Life 

(years)

Air conditioners, air cooled

0–65,000 Any Single package SEER 11.06 15

Any Split SEER 11.09 15

65,000–

135,000

Electric or none Split and single package EER 9.63 15

Other Split and single package EER 9.63 15

135,000–

240,000

Electric or none Split and single package EER 9.28 15

Other Split and single package EER 9.28 15

240,000–

760,000

Electric or none Split and single package EER 8.92 15

Other Split and single package EER 8.92 15

> 760,000

Electric or none Split and single package EER 8.63 15

Other Split and single package EER 8.63 15

Air conditioners, water or evaporatively cooled

0–65,000 Any Split and single package EER 10.50 19

Any Split and single package EER 10.50 19

65,000–

135,000

Electric or none Split and single package EER 10.75 19

Other Split and single package EER 10.58 19

135,000–

240,000

Electric or none Split and single package EER 10.04 19

Other Split and single package EER 9.87 19

>240,000

Electric or none Split and single package EER 10.04 19

Other Split and single package EER 9.87 19

Heat pumps, air cooled

0–65,000 Any Single package SEER 11.33 15

Any Split SEER 11.33 15

65,000–

135,000

Electric or none Split and single package EER 9.61 15

Other Split and single package EER 9.61 15

135,000–

240,000

Electric or none Split and single package EER 9.27 15

Other Split and single package EER 9.27 15

> 240,000

Electric or none Split and single package EER 8.92 15

Other Split and single package EER 8.92 15

Heat pumps, water source

0–17,000 All All EER 10.09 19

17,000–65,000 All All EER 10.46 19

65,000–

135,000 All All EER 10.99 19

135,000– All All EER 10.99 19
36

Equipment Category Capacity

(Btu/h) Heating Section Equipment Subcategory Efficiency Metric

Average 

Efficiency

Life 

(years)

240,000

Heat pumps, ground water source 0–135,000 All All EER 14.53 19

Heat pumps, ground source 0–135,000 All All EER 11.89 19

Heat pumps, air cooled

0–65,000 Any Single package HSPF 6.93 19

Any Split HSPF 7.04 19

65,000–

135,000

Electric or none Split and single package COP47 3.03 19

Other Split and single package COP47 3.03 19

135,000–

240,000

Electric or none Split and single package COP47 2.94 19

Other Split and single package COP47 2.94 19

> 240,000

Electric or none Split and single package COP47 2.94 19

Other Split and single package COP47 2.94 19

Heat pumps, water source

0–17,000 All All COP68 3.88 19

17,000–

135,000 All All COP68 3.88 19

Heat pumps, ground water source 0–135,000 All All COP50 NA 19

Heat pumps, ground source 0–135,000 All All COP32 NA 19

COP32 heating COP at 32°F ground source temperature

COP47 heating COP at 47°F outdoor air source temperature

COP50 heating COP at 50°F ground water source temperature

COP68 heating COP at 68°F water source temperature

HSPF heating seasonal performance factor

NA analysis incomplete
37

Table 32 Estimated Water Chilling Equipment Efficiencies for Pre-1980 Construction

Equipment Category Capacity

(tons)

Equipment 

Subcategory

Efficiency 

Metric

Average 

Efficiency

Life 

(years)

Chiller, air cooled, electrically operated

<150 All COP 2.70 23

150–300 All COP 2.64 23

> 300 All COP 2.64 23

Chiller, water cooled, electrically operated

< 150 Reciprocating COP 3.98 23

150–300 Reciprocating COP 3.98 23

> 300 Reciprocating COP 3.98 23

Chiller, water cooled, electrically operated

<150 Screw/scroll COP 4.13 23

150–300 Screw/scroll COP 4.50 23

> 300 Screw/scroll COP 5.11 23

Chiller, water cooled, electrically operated

< 150 Centrifugal COP 4.53 23

150–300 Centrifugal COP 4.93 23

> 300 Centrifugal COP 5.54 23

Chiller, air cooled, absorption, single effect All - COP 0.55 23

Chiller, water cooled absorption, single effect All - COP 0.69 23

Chiller, double effect, direct fired All - COP 0.98 23

Chiller, double effect, indirect fired All - COP 0.98 23

Table 33 Estimated Packaged Terminal Cooling Equipment Efficiencies for Pre-1980 Construction

Equipment Category Capacity

(Btu/h)

Efficiency 

Metric

Average 

Efficiency

Life 

(years)

PTAC

9,000 EER 9.79 10

12,000 EER 9.22 10

PTHP

9,000 EER 9.67 10

12,000 EER 9.09 10

PTHP-heating

9,000 COP47 2.86 10

12,000 COP47 2.78 10

PTAC < 42 × 16 in.

9,000 EER 8.82 10

12,000 EER 8.24 10

PTHP < 42 × 16 in.

9,000 EER 8.76 10

12,000 EER 8.18 10

PTHP heating < 42 × 16 in.

9,000 COP47 2.69 10

12,000 COP47 2.60 10

COP47 heating COP at 47°F outdoor air source temperature

HSPF heating seasonal performance factor

NA analysis incomplete

PTAC packaged terminal air-conditioning

PTHP packaged terminal heat pump
38

Table 34 Estimated Space Heating Equipment Efficiencies for Pre-1980 Construction

Equipment Category Capacity Efficiency 

Metric

Average 

Efficiency

Life 

(years)

Furnace

< 225 kBtu/h Ec 0.80 15

≥ 225 kBtu/h Ec 0.80 15

Duct furnace All Ec 0.80 15

Unit heater, gas All Ec 0.80 15

Boiler, gas, hot water

< 300 kBtu/h Et 0.73 30

300–2500 kBtu/h Et 0.74 30

> 2500 kBtu/h Et 0.76 30

Ec combustion efficiency (1-flue losses)

Et thermal efficiency

Table 35 Estimated Water Heating Equipment Efficiencies for Pre-1980 Construction

Equipment Category Capacity Efficiency 

Metric

Average 

Efficiency

Life 

(years)

Electric storage water heater

< 12 kW EF NA 7

> 12 kW SL NA 7

Gas storage water heater

< 75,000 Btu/h EF NA 7

> 75,000, <155,000 Btu/h

Et 0.80 7

SL NA 7

> 155,000 Btu/h

Et 0.80 7

SL NA 7

Gas instantaneous water heater

50–200 kBtu/h EF NA 15

> 200 Kbtu/h, < 10 gal Et 0.80 15

> 200 Kbtu/h, > 10 gal

Et 0.79 15

SL NA 15

Hot water supply boiler, gas

> 300, < 12,500 kBtu/h, < 10 gal Et 0.79 25

> 300, < 12,500 kBtu/h, > 10 gal

Et 0.78 25

SL NA 25

Ec combustion efficiency (1-flue losses)

EF energy factor

Et thermal efficiency

SL standby loss (rating to be defined either in Btu/h or in % per hour of stored water heat above ambient)

NA analysis incomplete

5.4.4 Fan Efficiencies

EnergyPlus requires the fan pressure rise, total efficiency, motor efficiency, and fraction of the 

motor in the air stream. For all cases, we assumed that the fraction of the motor in the air stream 

is 1.0. The other inputs are summarized in Table 34 for each fan type. Electrical motor 

efficiencies must comply with the requirements of the Energy Policy Act of 1992, which are 
39

listed in Table 10.8 of Standard 90.1-2004. To simplify the standard implementation, we assume 

all motors are open, four-pole, 1800-rpm. Table 36 lists nominal motor efficiency. The actual 

motor efficiency is determined for each case automatically by applying the standard after a sizing 

run is completed. Fan system flow rates are determined by EnergyPlus during system sizing.

Table 36 Fan System Inputs

System Type

Pressure Rise Fan 

Mechanical 

Efficiency

Total Fan

Efficiency**

Nominal 

Motor 

in. w.c. Pa Efficiency

Exhaust fans* 0.5 125 (a) 0.338 (a)

Unit heaters 0.2 50 0.650 0.536 0.825

PTAC and FCU fans 1.33 330 0.650 0.520 0.800

CAV < 7,487 cfm 2.5 622 0.650 (b) (c)

CAV > 7,487 cfm, < 20,000 cfm 4.46 1110 0.650 (b) (c)

CAV > 20,000 cfm 4.09 1,018 0.650 (b) (c)

VAV < 4,648 cfm 4.0 995 0.650 (b) (c)

VAV > 4,648 cfm, < 20,000 cfm 6.32 1572 0.650 (b) (c)

VAV > 20,000 cfm 5.58 1388 0.650 (b) (c)

* Exhaust fans are modeled as exterior loads, so only the total efficiency is important.

** Total fan efficiency is the product of fan mechanical efficiency and nominal motor efficiency. For example, a 

nominal motor efficiency of 85% and a fan mechanical efficiency of 65% produce a total fan efficiency of 55.25%.

Motor nameplate horsepower is assumed to be the first available motor size in ASHRAE 90.1-2004, Table 10.8 

greater than 110% of the motor brake horsepower, as calculated by the pressure rise and fan mechanical efficiency 

shown in Table 38 and the fan airflow as sized in the EnergyPlus simulation.

Exhaust fans typically have lower total efficiencies than space-conditioning fans. We assume a 

pressure rise of 0.5 in. w.c. (125 Pa) and a total fan efficiency of 0.338 for reference building 

exhaust fans. Because the heat from exhaust fans is released to the outdoors, only their total 

efficiencies are important. For space-conditioning fans, nominal motor efficiency would be 

important if one were to test the effect of lessening the fraction of motor heat in the air stream. 

Although the reference building models use 1.0 for that fraction, nominal motor efficiencies 

were chosen from 90.1-2004, Table 10.8, for consistency with typical practice. The two 

remaining model inputs that determine the power draw of the fan and the amount of fan heat 

gained by the space are fan mechanical efficiency and pressure rise. For simplicity, the reference

building models use one fan mechanical efficiency value, 0.65, and vary the pressure rise to 

achieve the desired fan power.

For unit heaters, we assumed a pressure rise of 0.2 in. w.c. (50 Pa) and a fan motor efficiency of 

0.825. For all PTACs and FCUs, we assumed a pressure rise of 1.33 in. w.c. (330 Pa) and a 

motor efficiency of 0.80. This corresponds to a power per flow rate of 0.3 W/cfm (636 W/m3

/s), 

corresponding with Standard 90.1-2007, Appendix G methodology. The pressure rise values of 

constant- and variable-volume air handlers are chosen to most closely approximate the fan power 

limitation determined in Standard 90.1-2004, Table 6.5.3.1. Below 5 hp (3.7 kW), which 

corresponds to 7,487 cfm at 2.5 in. w.c. (3.53 m3

/S at 620 Pa) for constant-volume fans and 

4,648 cfm at 4.0 in. w.c. (2.19 m3/s at 1000 Pa) for variable-volume, fans are not regulated by 

these limitations. Representative pressure rises are assumed in these cases (see Table 34). 
40

Additionally, 2.0 in. w.c. (498 Pa) is added to fans in the hospital and outpatient healthcare 

models to account for extra filtration.

5.4.5 Cooling Equipment Efficiencies

EnergyPlus requires the efficiency of cooling equipment to be input as the COP for the 

compressors and condenser fans. We used an automated routine that looks up the equipment 

efficiencies from Standard 90.1-2004 based on equipment type and size determined from an 

EnergyPlus sizing run. These efficiencies reported in Standard 90.1-2004 include the energy of 

the supply air fan. The efficiencies of small residential size equipment are reported as SEER, 

which must first be converted to EER. We use an approximation developed by Nexant for the 

Public Utilities Commission of Texas (2003), based on data from Carrier Corporation for 

conversion from SEER to EER.

EER = SEER ⋅ 0.697 + 2.0394

The COP of a unit is simply the cooling power output (Qcool) divided by the electrical power 

input (Pelec) in consistent units: 

COP = Qcool Pelec

The EER is the cooling power output in Btu divided by the electrical power input in W and 

requires a simple unit conversion to arrive at the COP:

COP = EER / 3.412

However, energy modeling software requires the COPcomp of the compressor as an input, not the 

overall COP of the cooling equipment. The EER values specified in ASHRAE 90.1-2004 refer 

to overall efficiencies, so an extra calculation must be done to obtain COPcomp. The COPcomp

value is calculated by subtracting the power of the supply fan rated at ARI standard conditions 

from the total power input to the unit. To approximate subtraction at ARI standard conditions, 

PNNL has developed the following relationship between COPcomp and EER (PNNL 2004), with 

R = 0.12 as a reasonable value to represent a broad class of products. R represents the ratio of 

supply fan power to total equipment power at the rating condition. 

R

EER R COPcomp −

+ = 1( / 3.413)

5.4.6 Refrigeration

Walk-in coolers and freezers are included in all commercial kitchens, based on data from 

Westphalen et al. (1996). The kitchen refrigeration systems are listed in Table 37 and Table 38. 

The refrigeration systems in the supermarket reference building are based on Westphalen et al. 

(2006) Faramarzi and Walker (2004), Deru and MacDonald (2007), and MacDonald and Deru 

(2007). The supermarket refrigeration systems are listed in Table 39 through Table 41.
41

Table 37 Walk-In Refrigeration System Descriptions (IP Units)

Building Type

Area 

(ft2)

Length

(ft)

Cooling

Capacity

(kBtu/h) COP

Evaporator

Fan

(W)

Condenser

Fan

(W)

Lighting

(W/ft2)

Defrost

(W)

AntiSweat

(W)

Case

Temp. 

(°F)

Heat 

Rejection

Location

Walk-In Coolers

Primary School 120 12 9.2 3 200 350 1 0.00 0 35 Outdoors

Secondary School 240 24 19.1 3 400 750 1 0.00 0 35 Outdoors

Quick Service Restaurant 100 10 7.7 3 200 330 1 0.00 0 35 Outdoors

Full Service Restaurant 100 10 7.7 3 200 330 1 0.00 0 35 Outdoors

Large Hotel 120 12 9.2 3 200 350 1 0.00 0 35 Outdoors

Hospital 360 29 27.0 3 600 1000 1 0.00 0 35 Outdoors

Walk-In Freezers

Primary School 120 12 9.2 1.5 250 350 1 2000 0 –10 Outdoors

Secondary School 240 24 18.3 1.5 500 750 1 3000 0 –10 Outdoors

Quick Service Restaurant 80 8 5.7 1.5 180 329 1 2000 0 –10 Outdoors

Full Service Restaurant 80 8 5.7 1.5 180 329 1 2000 0 –10 Outdoors

Large Hotel 120 24 9.2 1.5 250 350 1 2000 0 –10 Outdoors

Hospital 360 36 27.5 1.5 760 1000 1 4000 0 –10 Outdoors
42

Table 38 Walk-In Refrigeration System Descriptions (SI Units)

Building Type Area 

(m2)

Length

(m)

Cooling

Capacity

(kW)

COP

Evaporator

Fan

(W)

Condenser

Fan

(W)

Lighting

(W/m2)

Defros

t (W)

AntiSweat

(W)

Case

Temp. 

(°C)

Heat 

Rejection

Location

Walk-In Coolers

Primary School 11.2 3.7 2.7 3 200 350 10.8 0.00 0 1.7 Outdoors

Secondary School 22.3 7.3 5.6 3 400 750 10.8 0.00 0 1.7 Outdoors

Quick Service Restaurant 9.3 3.0 2.2 3 200 330 10.8 0.00 0 1.7 Outdoors

Full Service Restaurant 9.3 3.0 2.2 3 200 330 10.8 0.00 0 1.7 Outdoors

Large Hotel 11.2 3.7 2.7 3 200 350 10.8 0.00 0 1.7 Outdoors

Hospital 33.5 8.9 7.9 3 600 1000 10.8 0.00 0 1.7 Outdoors

Walk-In Freezers

Primary School 11.2 3.7 2.7 1.5 250 350 10.8 2000 0 –23.3 Outdoors

Secondary School 22.3 7.3 5.4 1.5 500 750 10.8 3000 0 –23.3 Outdoors

Quick Service Restaurant 7.4 2.4 1.7 1.5 180 329 10.8 2000 0 –23.3 Outdoors

Full Service Restaurant 7.4 2.4 1.7 1.5 180 329 10.8 2000 0 –23.3 Outdoors

Large Hotel 11.2 7.3 2.7 1.5 250 350 10.8 2000 0 –23.3 Outdoors

Hospital 33.5 11.0 8.1 1.5 760 1000 10.8 4000 0 –23.3 Outdoors
43

Table 39 Supermarket Refrigeration System Descriptions (IP Units)

Building Type Area 

(ft2)

Length

(ft)

Cooling

Capacity

(Btu/h/ft)

Evaporator

Fan

(W/ft)

Lighting

(W/ft)

Defrost

(W/ft)

AntiSweat

(W/ft)

SST

(°F)

Case

Temp.

(°F)

Compresso

r Rack

Medium Temperature

Multideck meat cases 120 1500 26.7 11.8 135 20 15 36 A

Other multideck cases 260 1500 12.5 18.3 0 0 15 36 A

Meat walk-in 400 50 400 50 400 50 0 15 36 C

Other walk-in 2600 325 2600 325 2600 325 0 15 36 C

Low Temperature

Reach-in cases 268 560 20 33 400 71 –25 5 B

Single-level open cases 128 550 10 0 420 24 –25 10 B

Walk-in freezer 1000 125 640 32 8 232 0 –25 –10 D

Table 40 Supermarket Refrigeration System Descriptions (SI Units)

Building Type Area 

(m2)

Length

(m)

Cooling 

Capacity

(W/m)

Evaporator

Fan

(W/m)

Lighting

(W/m)

Defrost

(W/m)

AntiSweat

(W/m)

SST

(°C)

Case

Temp.

(°C)

Compresso

r Rack

Medium Temperature

Multideck meat cases 36.6 1442 88 39 443 66 –9.4 2.2 A

Other multideck cases 79.2 1442 41 60 0 0 –9.4 2.2 A

Meat walk-in 37.2 15.2 385 164 1312 164 0 –9.4 2.2 C

Other walk-in 241.5 99.1 2500 1066 8530 1066 0 –9.4 2.2 C

Low Temperature

Reach-in cases 81.7 538 66 108 1312 233 –31.7 –15.0 B

Single-level open cases 39.0 529 33 0 1378 79 –31.7 –12.2 B

Walk-in freezer 92.9 38.0 615 105 26 761 0 –31.7 –23.3 D
44

Table 41 Supermarket Compressor Descriptions

Compressor 

Rack System Type COP

Condenser

Fan

(W)

Condenser 

Type

Heat 

Rejection 

Location

A Medium temperature 2.5 4500 Air cooled Outdoors

B Low temperature 1.3 4500 Air cooled Outdoors

C Medium temperature 2.5 4500 Air cooled Outdoors

D Low temperature 1.3 4500 Air cooled Outdoors
45

6.0 Weighting Factors

The weighting factors characterize the number of buildings that are similar to each reference

building type in each location. The weighting factors allow information from the individual 

reference buildings to be expanded to represent all buildings of this type in a region or combined 

to represent the whole country. Data for developing the weighting factors for U.S. commercial 

buildings are limited; CBECS is the best publicly available source for existing buildings. The 

database provides a wealth of information about the operational characteristics of buildings, but 

the number of buildings is limited and some of the data are masked to protect building identity. 

These limitations make it difficult to develop reliable statistical analysis across all building types 

and locations. The economic census from the U.S. Department of Commerce (U.S. Census 

Bureau 2005) contains economic data for commercial building activity by building type. 

However, it is difficult to determine building area from these data and to divide the building 

types into the subtypes such as small, medium, and large office buildings. 

The McGraw-Hill Construction Projects Starts Database draws from permit data for new 

commercial building starts in the United States and represents more than 90% of new 

commercial buildings. Data are collected in real time and the collection process is independently 

monitored to ensure most U.S. commercial construction is covered. The strength of this database 

lies in the number of samples, the frequency of data collection, the detailed data about location of 

the projects down to the local community level, and the fact that high-rise residential buildings 

are included (contrary to CBECS). A weakness is the lack of characteristic data.

Jarnagin and Bandyopadhyay (2010) analyzed the McGraw-Hill database from 2003 to 2007 to 

develop weighting factors for the new construction reference buildings. Total building area for 

each model type and climate zone was determined over the five-year period. These numbers 

were divided by five to find the annual average then divided by the area of the reference

buildings to find the weighting factors shown in Table 42.

Weighting factors for the pre-1980 and post-1980 reference buildings have not been developed,

because adequate data about the existing building stock have not been identified. Weighting 

factors may be developed when data become available.
46

Table 42 New Construction Reference Building Weighting Factors

Building Type

Climate Zone

1A 2A 2B 3A 3B 3C 4A 4B 4C 5A 5B 6A 6B 7 8

Small Office 201.9 2559.5 695.7 2316.1 1142.2 187.0 2251.0 113.9 294.8 2213.0 774.1 580.2 72.7 77.8 11.3

Medium Office 31.9 200.5 72.0 188.9 176.4 33.5 293.5 9.0 48.3 261.4 84.4 73.6 8.6 8.1 1.7

Large Office 2.7 8.6 1.6 11.8 7.6 3.1 30.0 0.0 4.1 11.7 3.2 3.5 0.0 0.3 0.0

Primary School 11.4 167.0 29.4 169.0 79.8 8.5 160.1 5.4 16.8 164.6 40.0 30.1 6.7 4.2 0.6

Secondary School 10.1 95.5 14.4 118.8 51.4 6.9 126.3 4.0 15.2 143.2 27.5 26.1 5.4 4.7 0.8

Stand-Alone Retail 118.9 1176.9 268.5 1264.6 662.8 101.3 1349.3 63.1 227.1 1818.0 420.0 502.7 48.3 57.5 7.2

Strip Mall 80.8 582.6 149.1 600.2 367.9 60.8 592.9 13.2 62.8 601.5 118.4 89.8 9.4 4.0 0.8

Supermarket 3.2 48.5 13.9 58.2 36.0 4.9 93.8 1.6 10.8 113.4 15.6 24.7 2.8 3.0 0.5

Quick Service 

Restaurant 41.3 484.9 107.4 538.8 334.3 36.6 471.0 28.2 75.7 680.1 135.8 134.3 16.4 18.9 1.2

Full Service 

Restaurant 21.7 254.0 59.1 267.7 114.2 13.9 305.9 14.0 24.6 344.2 74.7 74.6 9.6 8.8 0.3

Small Hotel 3.1 88.1 9.1 82.0 34.8 6.7 96.3 6.2 12.0 111.7 27.4 32.6 9.4 6.3 1.2

Large Hotel 11.8 67.3 13.5 68.8 85.9 11.4 103.8 4.0 13.3 99.6 21.6 24.6 6.3 4.2 0.4

Hospital 2.2 26.2 5.3 25.6 14.9 2.1 33.7 1.2 5.8 44.5 12.0 12.1 1.3 1.8 0.1

Outpatient 

Healthcare

12.0 183.4 43.4 187.8 88.8 19.8 264.3 7.5 58.5 342.0 70.4 110.7 10.8 12.6 0.7

Warehouse 88.8 658.6 147.6 754.2 584.3 39.1 621.8 17.2 110.7 910.1 175.0 118.4 12.5 11.0 0.6

Midrise Apartment 100.8 428.9 36.6 323.6 338.1 102.2 664.3 8.6 145.5 439.9 124.9 122.9 22.1 12.7 0.0
47

7.0 Conculsions

The reference building models represent important starting points for energy simulation 

exercises and form standard reference points for building energy analysis projects. The models 

are being used for research projects by DOE, national laboratories, and industry to perform 

research on advanced building systems, assess the impact of new policies, and advance building 

energy codes and standards. They continue to evolve and expand; new versions are available for 

public use. The models are available as EnergyPlus input files on the DOE Web site 

(http://commercialbuildings.energy.gov/reference_buildings.html). Spreadsheet scorecards are 

also available for each building type to document the model parameters and annual energy 

performance by location.
48

8.0 References

AIA. (2001). AIA Guidelines for Design and Construction of Hospital and Health Care 

Facilities: 2001 Edition. Washington, D.C.: American Institute of Architects. 

ASHRAE. (1989). Energy Efficient Design of New Buildings Except Low-Rise Residential 

Buildings. ANSI/ASHRAE/IESNA Standard 90.1-1989. Atlanta, GA: American Society of 

Heating, Refrigerating and Air-Conditioning Engineers.

ASHRAE. (1999). Ventilation for Acceptable Indoor Air Quality. ANSI/ASHRAE Standard 

62-1999. Atlanta, GA: American Society of Heating, Refrigerating and Air-Conditioning 

Engineers.

ASHRAE. (2001). Energy Standard for Buildings Except Low-Rise Residential Buildings. 

ANSI/ ASHRAE/IESNA Standard 90.1-2001. Atlanta, GA: American Society of Heating, 

Refrigerating and Air-Conditioning Engineers.

ASHRAE. (2004a). Energy Standard for Buildings Except Low-Rise Residential Buildings. 

ANSI/ ASHRAE/IESNA Standard 90.1-2004. Atlanta, GA: American Society of Heating, 

Refrigerating and Air-Conditioning Engineers.

ASHRAE. (2004b). Ventilation for Acceptable Indoor Air Quality. ANSI/ASHRAE Standard 

62.1-2004. Atlanta, GA: American Society of Heating, Refrigerating and Air-Conditioning 

Engineers.

ASHRAE. (2004c). 90.1 User’s Manual ANSI/ASHRAE/IESNA Standard 90.1-2004. Atlanta, 

GA: American Society of Heating, Refrigerating and Air-Conditioning Engineers.

ASHRAE. (2007). 2007 ASHRAE HVAC Applications Handbook. Atlanta, GA: American 

Society of Heating, Refrigerating and Air-Conditioning Engineers.

ASHRAE. (2009). Advanced Energy Design Guides. Atlanta, GA: American Society of 

Heating, Refrigerating and Air-Conditioning Engineers. Available at www.ashrae.org/ 

publications/page/1604. Last accessed October 2009.

Baldor Electric Company. (1998). Baldor Motors and Drives: AC Elevator Drives. Fort Smith, 

AR: Baldor Electric Company.

Beyer, R. (2009). “Specification Series: Elevators - First Things First.” Atlanta, GA: Elevator 

Advisors, Inc. First appeared in Architectural Record, November 1992. McGraw-Hill, Inc. 

Available at www.elevatoradvisors.com/docs/BeyerSpecSeries.pdf. Last accessed October 2009.

Briggs, R.S.; Crawley, D.B.; Schliesing, J.S. (1987). Analysis and Categorization of the Office 

Building Stock, Topical Report. Des Plains, IL: Gas Technology Institute. GRI-87/0244. 

Briggs, R.S.; Lucas, R.G.; Taylor, T. (2003). “Climate Classification for Building Energy 

Codes and Standards: Part 2 - Zone Definitions, Maps and Comparisons, Technical and 

Symposium Papers.” ASHRAE Winter Meeting, Chicago, IL, January 2003. Atlanta, GA: 

American Society of Heating, Refrigerating and Air-Conditioning Engineers. Available at 

http://resourcecenter.pnl.gov/html/ ResourceCenter/1420.html. Last accessed October 2009.
49

Brown, S.L. (2007). “Dedicated Outdoor Air System for Commercial Kitchen Ventilation.” 

ASHRAE Journal 49(7), 24–35. Atlanta, GA: American Society of Heating, Refrigerating and 

Air-Conditioning Engineers.

CEC. (2004). Design Guide 2 Improving Commercial Kitchen Ventilation System Performance: 

Optimizing Makeup Air. Sacramento, CA: California Energy Commission.

DeChiara, J.; Crosbie, M.J. (2001). Time-Saver Standards for Building Types, 4th ed. McGrawHill Professional.

Deru, M.; MacDonald, M. (2007). “Wal-Mart Experience: Part Two.” ASHRAE Journal

49(10):22–27. Golden, CO: National Renewable Energy Laboratory, NREL/JA-550-42503. 

Available at www.nrel.gov/docs/fy09osti/45742.pdf. Last accessed October 2009.

DOE. (2005). Map of DOE’s Proposed Climate Zones. Available at www.energycodes.gov/ 

implement/pdfs/color_map_climate_zones_Mar03. Last accessed July 2010.

Doebber, I.; Bonnema, E.; Pless, S.; Torcellini, P. (2009). Technical Support Document: 

Development of the Advanced Energy Design Guide for Small Hospitals and Health Care 

Facilities – 30% Energy Savings. Golden, CO: National Renewable Energy Laboratory,

NREL/TP-550-46314. Available at www.nrel.gov/docs/fy10osti/46314.pdf. Last accessed 

October 2009. 

EIA. (2002). 1999 Commercial Buildings Energy Consumption Survey. Washington, DC: EIA. 

Available at www.eia.doe.gov/emeu/cbecs/1999publicuse/99microdat.html. Last accessed 

October 2009. 

EIA. (2005). 2003 Commercial Buildings Energy Consumption Survey. Washington, DC: 

Energy Information Administration. Available at www.eia.doe.gov/emeu/cbecs/ 

cbecs2003/introduction.html. Last accessed October 2009. 

Faramarzi, R.T.; Walker, D.H. (2004). Investigation of Secondary Loop Supermarket 

Refrigeration Systems. 500-04-013. Sacramento, CA: California Energy Commission.

Fisher, D. (2003). “Predicting Energy Consumption.” ASHRAE Journal 45(6), K8–K13. 

Atlanta, GA: American Society of Heating, Refrigerating and Air-Conditioning Engineers.

GGHC. (2007). Green Guide for Health Care: Best Practices for Creating High Performance 

Healing Environments, Version 2.2. www.gghc.org. Last accessed October 2009.

Gowri, K.; Halverson, M.A.; Richman, E.E. (2007). Analysis of Energy Saving Impacts of 

ASHRAE 90.1-2004 for the State of New York. Richland, WA: Pacific Northwest National 

Laboratory, PNNL-16770. 

Griffith, B.; Long, N.; Torcellini, P.; Judkoff, R.: Crawley, D.; Ryan, J. (2007). Assessment of the 

Technical Potential for Achieving Net Zero-Energy Buildings in the Commercial Sector. 

Golden, CO: National Renewable Energy Laboratory. NREL/TP-550-41957. Available at 

www.nrel.gov/docs/fy08osti/41957.pdf. Last accessed February 2010.

Hendron, R. (2007). Building America Research Benchmark Definition, Updated December 20, 

2007. Golden, CO: National Renewable Energy Laboratory, NREL/TP-550-42662. Available 

at www.nrel.gov/docs/fy08osti/42662.pdf. Last accessed October 2009.
50

Huang, J.; Akbari, H.; Rainer, L.; Ritshard, R. (1991). 481 Prototypical Commercial Buildings 

for 20 Urban Market Areas. Berkeley, CA: Lawrence Berkeley National Laboratory.

Huang, J.; Franconi, E. (1999). Commercial Heating and Cooling Loads Component Analysis. 

Berkeley, CA: Lawrence Berkeley National Laboratory, LBL-37208. 

Huang, J.; Roberson, J.A.; Sezgen, O. (2005). Analysis of 1999 CBECS Data by Commercial 

Building Type. Draft. Berkeley, CA: Lawrence Berkeley National Laboratory, LBNL-57457.

ICC. (2003). 2003 International Building Code. Country Club Hills, IL: International Code 

Council, Inc.

Jarnagin, R.E.; Liu, B.; Winiarski, D.W.; McBride, M.F.; Suharli, L.; Walden, D. (2006). 

Technical Support Document: The Development of the Advanced Energy Design Guide for 

Small Office Buildings. Richland, WA: Pacific Northwest National Laboratory, PNNL-16250. 

Jarnagin, R.E.; Bandyopadhyay, G. (2010). Determination of Weighting Factors for the 

ASHRAE Commercial Building Prototypes for Standard 90.1-2010. Richland, WA: Pacific 

Northwest National Laboratory, PNNL-19116.

Jiang, W.; Jarnagin, R.E.; Gowri, K.; McBride, M.; Liu, B. (2008). Technical Support 

Document: The Development of the Advanced Energy Design Guide for Highway Lodging 

Buildings. Richland, WA: Pacific Northwest National Laboratory, PNNL-17875. 

Liu, B.; Jarnagin, R.E.; Winiarski, D.W.; Jiang, W.; McBride, M.; Crall, G.C. (2006). Technical 

Support Document: The Development of the Advanced Energy Design Guide for Small Retail 

Buildings. Richland, WA: Pacific Northwest National Laboratory, PNNL-16031. 

Liu, B.; Jarnagin, R.E.; Jiang, W.; Gowri, K. (2007). Technical Support Document: The 

Development of the Advanced Energy Design Guide for Small Warehouse and Self-Storage 

Buildings. Richland, WA: Pacific Northwest National Laboratory, PNNL-17056. 

MacDonald, M.; Deru, M. (2007). “Wal-Mart Experience: Part One.” ASHRAE Journal 49(9) 

14–25; Golden, CO: National Renewable Energy Laboratory, NREL/JA-550-42015. Available 

at www.nrel.gov/docs/fy09osti/45742.pdf. Last accessed October 2009.

McGraw Hill. (2005). Dodge Database. McGraw Hill Construction. Available at

http://dodge.construction.com/. Last accessed October 2009. 

NCDC. (1993). Solar and Meteorological Surface Observational Network (SAMSON), 1961-

1990, 3-volume CD-ROM set. NCDC, Asheville, NC: National Climatic Data Center.

Persily, A.K. (1998). Airtightness of Commercial and Institutional Buildings, Proceedings of 

ASHRAE Thermal Envelopes VII Conference. Atlanta, GA: American Society of Heating, 

Refrigerating and Air-Conditioning Engineers. 

Pless, S.; Torcellini, P.; Long, N. (2007). Technical Support Document: Development of the 

Advanced Energy Design Guide for K-12 Schools—30% Energy Savings. Golden, CO: National 

Renewable Energy Laboratory, NREL /TP-550-42114. Available at www.nrel.gov/docs/ 

fy07osti/42114.pdf. Last accessed October 2009.

PNNL. (2004). Technical Support Document: Energy Efficiency Program for Commercial and 

Industrial Equipment: Advanced Notice of Proposed Rulemaking for Commercial Unitary Air 
51

Conditioners and Heat Pumps. For the U.S. Department of Energy. Richland, WA: Pacific 

Northwest National Laboratory. 

Public Utilities Commission of Texas. (2003). Deemed Savings, Installation & Efficiency 

Standards: Commercial and Industrial Cooling Equipment. Boulder, CO: Nexant, Inc. 

Available at www.puc.state.tx.us/rules/rulemake/27903/16_25.184-14.pdf. Last accessed 

October 2009. 

SGE. (2004). Design Guide 1 Improving Commercial Kitchen Ventilation System Performance: 

Selecting and Sizing Exhaust Hoods. Rancho Cucamonga, CA: Southern California Edison. 

Smith, V.A.; Fisher, D.R. (2001). “Estimating Food Service Loads and Profiles.” ASHRAE 

Transactions 2001, 107(2). Atlanta, GA: American Society of Heating, Refrigerating and AirConditioning Engineers.

Smith, V.A.; Young, R.; Spata, A.J.; Fisher, D. (1999). “Virtual vs. Real: Modeling the Energy 

Performance of a Quick Service Restaurant.” ASHRAE Transactions 1999, 105. Atlanta, GA: 

American Society of Heating, Refrigerating and Air-Conditioning Engineers.

Stocki, M.; Curcija, D.C.; Bhandari, M.S. (2005). The Development of Standardized Whole 

Building Simulation Assumptions for Energy Analysis for a Set of Commercial Buildings (draft 

May 31 2005). Amherst, MA: University of Massachusetts.

U.S. Census Bureau. (2005). 2002 Economic Census: Sector 23: Construction: Geographic 

Area Series: Value of Construction Work for Establishments by Type of Construction: 2002. 

Washington, DC: U.S. Department of Commerce. Available at http://factfinder.census.gov/ 

servlet/IBQTable?_bm=y&-geo_id=&-ds_name=EC0223A6&-_lang=en. Last accessed 

October 2009.

Westphalen, D.; Zogg, R.A.; Varone, A.F.; Foran, M.A. (1996). Energy Savings Potential for 

Commercial Refrigeration Equipment. For the U.S. Department of Energy. Cambridge, MA: 

Arthur D. Little, Inc.

Winiarski, D.W.; Jiang, W.; Halverson, M.A. (2006). Review of Pre- and Post-1980 Buildings 

in CBECS – HVAC Equipment. Richland, WA: Pacific Northwest National Laboratory.

Winiarski D.W.; Halverson, M.A.; Jiang, W. (2007a). Analysis of Building Envelope 

Construction in 2003 CBECS Pre-1980 Buildings. Richland, WA: Pacific Northwest National 

Laboratory. PNNL-SA-55594. 

Winiarski, D.W.; Jiang, W; Halverson, M.A. (2007b). Analysis of Building Envelope 

Construction in 2003 CBECS Post-1980 Buildings. Richland, WA: Pacific Northwest National 

Laboratory. PNNL-SA-55888. 

Winiarski, D.W.; Halverson, M.A.; Jiang, W. (2008). “DOE’s Commercial Building 

Benchmarks - Development of Typical Construction Practices for Building Envelope and 

Mechanical Systems from the 2003 CBECS.” In Proceedings of 2008 Summer Study on Energy 

Efficiency in Buildings, American Council for an Energy Efficient Economy.

Winiarski, D.W.; Halverson, M.A. (2008). Equipment Efficiency for Existing Benchmark 

Buildings. Internal report. Richland, WA: Pacific Northwest National Laboratory.
52

Appendix A Reference Building Internal Loads

Table A-1 Reference Building Zone Internal Loads (IP units)

Building Type/Zone

Area

ft2

Vol.

ft3

ft2/

person

1989

Lights

Wft2

2004

Lights

Wft2

Elec.

Proc.

W/ft2

Gas 

Proc. 

W/ft2

Vent. 

cfm

Exhst 

cfm

Infil. 

ACH 

SWH 

gal/h

Quick Service Restaurant 2,501 25,015

Dining 1,250 12,508 15.0 1.44 2.1 12.0 0.0 1667.3 0.0 0.64 0.0

Kitchen 1,250 12,508 200.0 1.55 1.2 28.0 120.0 93.8 3300.0 0.64 40.0

Attic 2,501 9,264 0.0 0.00 0.0 0.0 0.0 0.0 0.0 1.00 0.0

Hospital 241,350 3,138,208

Basement 40,250 322,083 400.0 0.70 1.1 0.8 0.0 2012.5 0.0 0.00 0.0

ER_Exam1_Mult4_Flr_1 300 4,201 50.0 3.84 2.7 1.5 0.0 140.0 0.0 0.24 1.0

ER_Exam2_Flr_1 300 4,201 50.0 3.84 2.7 4.0 0.0 140.0 0.0 0.42 1.0

ER_Exam3_Mult4_Flr_1 300 4,201 50.0 3.84 2.7 1.5 0.0 140.0 0.0 0.18 1.0

ER_Exam4_Flr_1 300 4,201 50.0 3.84 2.7 4.0 0.0 140.0 0.0 0.42 1.0

ER_Exam5_Mult4_Flr_1 300 4,201 50.0 3.84 2.7 2.0 0.0 140.0 0.0 0.24 1.0

Office1_Mult4_Flr_1 150 2,101 142.9 2.40 1.1 1.1 0.0 21.0 0.0 0.24 0.0

Lobby_Flr_1 15,875 222,303 140.0 1.29 1.5 0.1 0.0 2267.8 0.0 0.07 0.0

Corridor_Flr_1 6,125 85,772 1000.0 1.36 1.0 0.0 0.0 306.2 0.0 0.04 0.0

ER_NurseStat_Flr_1 13,300 186,248 160.0 2.10 1.1 1.4 0.0 6208.3 0.0 0.02 0.0

OR1_Flr_2 600 8,402 200.0 9.75 2.2 4.0 0.0 420.1 0.0 0.30 2.0

OR2_Mult5_Flr_2 600 8,402 200.0 9.75 2.2 4.0 0.0 420.1 0.0 0.12 2.0

OR3_Flr_2 600 8,402 200.0 9.75 2.2 4.0 0.0 420.1 0.0 0.18 2.0

OR4_Flr_2 2,400 33,609 200.0 7.89 2.2 4.0 0.0 1680.5 0.0 0.00 6.0

IC_PatRoom1_Mult5_Flr_2 225 3,150 200.0 3.84 0.8 3.0 0.0 105.0 0.0 0.24 0.0

IC_PatRoom2_Flr_2 300 4,201 200.0 3.84 0.8 3.0 0.0 140.0 0.0 0.42 0.0

IC_PatRoom3_Mult6_Flr_2 225 3,150 200.0 3.84 0.8 3.0 0.0 105.0 0.0 0.24 0.0

ICU_Flr_2 6,652 93,147 50.0 3.84 0.8 3.0 0.0 3104.9 0.0 0.09 0.0

ICU_NurseSat_Flr_2 7,199 100,806 200.0 2.17 1.0 2.0 0.0 719.9 0.0 0.00 0.0

Corridor_Flr_2 6,125 85,772 1000.0 1.36 1.0 0.0 0.0 122.5 0.0 0.04 0.0

OR_NurseSat_Flr_2 10,900 152,639 140.0 2.12 1.2 1.0 0.0 1557.1 0.0 0.05 0.0

PatRoom1_Mult10_Flr_3 225 3,150 200.0 2.19 0.7 2.0 0.0 105.0 0.0 0.24 1.0

PatRoom2_Flr_3 375 5,252 200.0 2.19 0.7 2.0 0.0 175.1 0.0 0.38 1.0

PatRoom3_Mult10_Flr_3 218 3,046 200.0 2.19 0.7 2.0 0.0 101.5 0.0 0.24 1.0

PatRoom4_Flr_3 375 5,252 200.0 2.19 0.7 2.0 0.0 175.1 0.0 0.38 1.0

PatRoom5_Mult10_Flr_3 225 3,150 200.0 2.19 0.7 2.0 0.0 105.0 0.0 0.24 1.0

PhysTherapy_Flr_3 5,250 73,519 200.0 2.50 0.9 1.5 0.0 393.7 0.0 0.00 1.0

PatRoom6_Flr_3 300 4,201 200.0 2.19 0.7 2.0 0.0 140.0 0.0 0.42 1.0

PatRoom7_Mult10_Flr_3 218 3,046 200.0 2.19 0.7 2.0 0.0 101.5 0.0 0.24 1.0

PatRoom8_Flr_3 300 4,201 200.0 2.19 0.7 2.0 0.0 140.0 0.0 0.42 1.0

NurseSat_Lobby_Flr_3 9,750 136,534 140.0 2.13 1.2 1.0 0.0 1392.8 0.0 0.00 0.0

Lab_Flr_3 2,850 39,910 200.0 2.10 1.4 4.0 0.0 285.0 0.0 0.00 2.0

Corridor_SE_Flr_3 6,100 85,422 1000.0 1.36 1.0 0.0 0.0 305.0 0.0 0.02 0.0

Corridor_NW_Flr_3 6,100 85,422 1000.0 1.36 1.0 0.0 0.0 305.0 0.0 0.02 0.0

PatRoom1_Mult10_Flr_4 225 3,150 200.0 2.19 0.7 2.0 0.0 105.0 0.0 0.24 1.0

PatRoom2_Flr_4 375 5,252 200.0 2.19 0.7 2.0 0.0 175.1 0.0 0.38 1.0

PatRoom3_Mult10_Flr_4 218 3,046 200.0 2.19 0.7 2.0 0.0 101.5 0.0 0.24 1.0

PatRoom4_Flr_4 375 5,252 200.0 2.19 0.7 2.0 0.0 175.1 0.0 0.38 1.0

PatRoom5_Mult10_Flr_4 225 3,150 200.0 2.19 0.7 2.0 0.0 105.0 0.0 0.24 1.0

Radiology_Flr_4 5,250 73,519 200.0 2.21 0.4 10.0 0.0 393.7 0.0 0.00 1.0

PatRoom6_Flr_4 300 4,201 200.0 2.19 0.7 2.0 0.0 140.0 0.0 0.42 1.0

PatRoom7_Mult10_Flr_4 218 3,046 200.0 2.19 0.7 2.0 0.0 101.5 0.0 0.24 1.0

PatRoom8_Flr_4 300 4,201 200.0 2.19 0.7 2.0 0.0 140.0 0.0 0.42 1.0

NurseSat_Lobby_Flr_4 9,750 136,534 140.0 2.13 1.2 1.0 0.0 1392.8 0.0 0.00 0.0

Lab_Flr_4 2,850 39,910 200.0 2.10 1.4 4.0 0.0 285.0 0.0 0.00 2.0

Corridor_SE_Flr_4 6,100 85,422 1000.0 1.36 1.0 0.0 0.0 305.0 0.0 0.02 0.0
53

Building Type/Zone

Area

ft2

Vol.

ft3

ft2/

person

1989

Lights

Wft2

2004

Lights

Wft2

Elec.

Proc.

W/ft2

Gas 

Proc. 

W/ft2

Vent. 

cfm

Exhst 

cfm

Infil. 

ACH 

SWH 

gal/h

Corridor_NW_Flr_4 6,100 85,422 1000.0 1.36 1.0 0.0 0.0 305.0 0.0 0.02 0.0

Dining_Flr_5 7,500 105,027 100.0 2.58 0.9 1.0 0.0 1500.0 0.0 0.34 0.0

NurseSat_Flr_5 11,200 156,840 140.0 2.12 1.2 1.0 0.0 1600.0 0.0 0.28 0.0

Kitchen_Flr_5 10,000 140,036 200.0 1.42 1.2 7.5 28.3 750.0 5300.0 0.33 150.0

Office1_Flr_5 750 10,506 142.9 2.40 1.1 1.0 0.0 105.0 0.0 0.52 0.0

Office2_Mult5_Flr_5 750 10,503 142.9 2.40 1.1 1.0 0.0 105.0 0.0 0.37 0.0

Office3_Flr_5 750 10,503 142.9 2.40 1.1 1.0 0.0 105.0 0.0 0.52 0.0

Office4_Mult6_Flr_5 150 2,101 142.9 2.40 1.1 1.0 0.0 20.0 0.0 0.49 0.0

Corridor_Flr_5 5,400 75,620 1000.0 1.36 1.0 0.0 0.0 270.0 0.0 0.29 0.0

Large Hotel 122,116 1,242,549

Basement 21,300 170,443 400.0 0.70 1.0 0.5 0.0 1065.0 0.0 0.00 0.0

Retail_1_Flr_1 722 9,385 66.7 3.54 1.5 1.0 0.0 216.6 0.0 0.56 0.0

Retail_2_Flr_1 836 10,868 66.7 3.54 1.5 1.0 0.0 250.8 0.0 0.09 0.0

Mech_Flr_1 1,768 22,983 0.0 0.80 1.5 0.5 0.0 88.4 0.0 0.11 0.0

Storage_Flr_1 1,020 13,260 500.0 0.37 0.9 0.3 0.0 153.0 0.0 0.11 0.0

Laundry_Flr_1 840 10,920 250.0 1.14 0.6 5.7 49.8 50.4 500.0 0.30 156.6

Cafe_Flr_1 2,033 26,428 15.0 1.46 1.3 0.5 0.0 2710.5 0.0 0.50 0.0

Lobby_Flr_1 14,081 183,056 33.3 1.88 1.1 0.8 0.0 8449.6 0.0 0.10 0.0

Room_1_Flr_3 420 4,200 280.0 1.77 1.1 0.6 0.0 30.0 0.0 0.37 1.3

Room_2_Flr_3 420 4,200 280.0 1.77 1.1 0.6 0.0 30.0 0.0 0.37 1.3

Room_3_Mult19_Flr_3 264 2,640 176.0 1.77 1.1 0.6 0.0 30.0 0.0 0.16 23.8

Room_4_Mult19_Flr_3 264 2,640 176.0 1.77 1.1 0.6 0.0 30.0 0.0 0.16 23.8

Room_5_Flr_3 420 4,200 280.0 1.77 1.1 0.6 0.0 30.0 0.0 0.37 1.3

Room_6_Flr_3 420 4,200 280.0 1.77 1.1 0.6 0.0 30.0 0.0 0.37 1.3

Corridor_Flr_3 4,191 41,915 1000.0 1.22 0.5 0.0 0.0 209.6 0.0 0.04 0.0

Room_1_Flr_6 420 4,200 280.0 1.77 1.1 0.6 0.0 30.0 0.0 0.72 1.3

Room_2_Flr_6 420 4,200 280.0 1.77 1.1 0.6 0.0 30.0 0.0 0.72 1.3

Room_3_Mult9_Flr_6 264 2,640 176.0 1.77 1.1 0.6 0.0 30.0 0.0 1.28 11.3

Banquet_Flr_6 3,570 35,699 15.0 2.56 1.3 6.3 0.0 4759.9 0.0 0.46 0.0

Dining_Flr_6 3,570 35,699 15.0 2.56 1.3 6.3 0.0 4759.9 0.0 0.46 0.0

Kitchen_Flr_6 1,112 11,120 200.0 1.56 1.2 47.2 149.9 83.4 4000.0 0.66 133.0

Corridor_Flr_6 4,436 44,361 1000.0 1.22 0.5 0.0 0.0 221.8 0.0 0.48 0.0

Large Office 498,588 6,291,164

Basement 38,353 306,899 400.0 0.70 1.0 0.4 0.0 1917.6 0.0 0.00 0.0

Perimeter_bot_ZN_3 3,374 30,371 200.0 1.50 1.0 0.7 0.0 337.4 0.0 0.25 0.0

Perimeter_bot_ZN_2 2,174 19,572 200.0 1.50 1.0 0.7 0.0 217.4 0.0 0.26 0.0

Perimeter_bot_ZN_1 3,374 30,371 200.0 1.50 1.0 0.7 0.0 337.4 0.0 0.25 0.0

Perimeter_bot_ZN_4 2,174 19,572 200.0 1.50 1.0 0.7 0.0 217.4 0.0 0.26 0.0

Core_bottom 27,258 245,391 200.0 1.50 1.0 0.7 0.0 2725.8 0.0 0.00 21.3

Perimeter_mid_ZN_3 3,374 30,371 200.0 1.50 1.0 0.7 0.0 337.4 0.0 0.25 0.0

Perimeter_mid_ZN_2 2,174 19,572 200.0 1.50 1.0 0.7 0.0 217.4 0.0 0.26 0.0

Perimeter_mid_ZN_1 3,374 30,371 200.0 1.50 1.0 0.7 0.0 337.4 0.0 0.25 0.0

Perimeter_mid_ZN_4 2,174 19,572 200.0 1.50 1.0 0.7 0.0 217.4 0.0 0.26 0.0

Core_mid 27,258 245,391 200.0 1.50 1.0 0.7 0.0 2725.8 0.0 0.00 21.3

Perimeter_top_ZN_3 3,374 30,371 200.0 1.50 1.0 0.7 0.0 337.4 0.0 0.65 0.0

Perimeter_top_ZN_2 2,174 19,572 200.0 1.50 1.0 0.7 0.0 217.4 0.0 0.66 0.0

Perimeter_top_ZN_1 3,374 30,371 200.0 1.50 1.0 0.7 0.0 337.4 0.0 0.65 0.0

Perimeter_top_ZN_4 2,174 19,572 200.0 1.50 1.0 0.7 0.0 217.4 0.0 0.66 0.0

Core_top 27,258 245,391 200.0 1.50 1.0 0.7 0.0 2725.8 0.0 0.40 21.3

Groundfloor_plenum 38,353 153,412 0.0 0.00 0.0 0.0 0.0 0.0 0.0 0.07 0.0

Midfloor_plenum 38,353 153,412 0.0 0.00 0.0 0.0 0.0 0.0 0.0 0.07 0.0

Topfloor_plenum 38,353 153,412 0.0 0.00 0.0 0.0 0.0 0.0 0.0 0.97 0.0

Medium Office 53,628 697,161

Perimeter_bot_ZN_3 2,232 20,086 200.0 1.57 1.0 0.7 0.0 223.2 0.0 0.26 0.0

Perimeter_bot_ZN_2 1,413 12,716 200.0 1.57 1.0 0.7 0.0 141.3 0.0 0.28 0.0

Perimeter_bot_ZN_1 2,232 20,086 200.0 1.57 1.0 0.7 0.0 223.2 0.0 0.26 0.0
54

Building Type/Zone

Area

ft2

Vol.

ft3

ft2/

person

1989

Lights

Wft2

2004

Lights

Wft2

Elec.

Proc.

W/ft2

Gas 

Proc. 

W/ft2

Vent. 

cfm

Exhst 

cfm

Infil. 

ACH 

SWH 

gal/h

Perimeter_bot_ZN_4 1,413 12,715 200.0 1.57 1.0 0.7 0.0 141.3 0.0 0.28 0.0

Core_bottom 10,587 95,280 200.0 1.57 1.0 0.7 0.0 1058.7 0.0 0.00 9.9

Perimeter_mid_ZN_3 2,232 20,086 200.0 1.57 1.0 0.7 0.0 223.2 0.0 0.26 0.0

Perimeter_mid_ZN_2 1,413 12,716 200.0 1.57 1.0 0.7 0.0 141.3 0.0 0.28 0.0

Perimeter_mid_ZN_1 2,232 20,086 200.0 1.57 1.0 0.7 0.0 223.2 0.0 0.26 0.0

Perimeter_mid_ZN_4 1,413 12,715 200.0 1.57 1.0 0.7 0.0 141.3 0.0 0.28 0.0

Core_mid 10,587 95,280 200.0 1.57 1.0 0.7 0.0 1058.7 0.0 0.00 9.9

Perimeter_top_ZN_3 2,232 20,086 200.0 1.57 1.0 0.7 0.0 223.2 0.0 0.66 0.0

Perimeter_top_ZN_2 1,413 12,716 200.0 1.57 1.0 0.7 0.0 141.3 0.0 0.67 0.0

Perimeter_top_ZN_1 2,232 20,086 200.0 1.57 1.0 0.7 0.0 223.2 0.0 0.66 0.0

Perimeter_top_ZN_4 1,413 12,715 200.0 1.57 1.0 0.7 0.0 141.3 0.0 0.67 0.0

Core_top 10,587 95,280 200.0 1.57 1.0 0.7 0.0 1058.7 0.0 0.40 9.9

Firstfloor_plenum 17,876 71,504 0.0 0.00 0.0 0.0 0.0 0.0 0.0 0.11 0.0

Midfloor_plenum 17,876 71,504 0.0 0.00 0.0 0.0 0.0 0.0 0.0 0.11 0.0

Topfloor_plenum 17,876 71,504 0.0 0.00 0.0 0.0 0.0 0.0 0.0 1.00 0.0

Midrise Apartment 33,741 337,378

G SW APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.24 3.5

G NW APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.24 3.5

OFFICE 950 9,498 474.9 2.04 1.0 1.2 0.0 40.0 0.0 0.24 0.0

G NE APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.24 3.5

G N1 APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.14 3.5

G N2 APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.14 3.5

G S1 APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.14 3.5

G S2 APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.14 3.5

M SW APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.24 3.5

M NW APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.24 3.5

M SE APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.24 3.5

M NE APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.24 3.5

M N1 APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.14 3.5

M N2 APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.14 3.5

M S1 APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.14 3.5

M S2 APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.14 3.5

T SW APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.59 3.5

T NW APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.59 3.5

T SE APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.59 3.5

T NE APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.59 3.5

T N1 APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.50 3.5

T N2 APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.50 3.5

T S1 APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.50 3.5

T S2 APARTMENT 950 9,498 380.0 0.36 0.4 0.5 0.0 90.0 0.0 0.50 3.5

T CORRIDOR 836 8,359 0.0 0.92 0.5 0.0 0.0 41.8 0.0 0.40 0.0

G CORRIDOR 836 8,359 0.0 0.92 0.5 0.0 0.0 41.8 0.0 0.05 0.0

M CORRIDOR 836 8,359 0.0 0.92 0.5 0.0 0.0 41.8 0.0 0.05 0.0

Outpatient Health Care 40,946 421,380

Floor 1 Anesthesia 108 1,080 0.0 3.0 2.0 0.0 129.6 144.0 0.30 1.0

Floor 1 Bio Haz 56 560 0.0 0.9 0.1 0.0 8.4 0.0 0.00 0.0

Floor 1 Café 420 4,200 10.8 0.9 1.0 0.0 780.4 0.0 0.17 0.0

Floor 1 Clean 126 1,260 53.8 1.2 2.0 0.0 37.8 0.0 0.00 0.0

Floor 1 Clean Work 165 1,650 53.8 1.2 2.0 0.0 49.5 0.0 0.00 0.0

Floor 1 Dictation 126 1,260 215.3 1.1 1.1 0.0 11.7 0.0 0.00 0.0

Floor 1 Dressing Room 45 450 215.3 1.1 1.1 0.0 4.2 0.0 0.71 0.0

Floor 1 Electrical Room 98 980 0.0 1.5 5.0 0.0 4.9 0.0 0.25 0.0

Floor 1 Elevator Pump Room 91 910 0.0 1.5 5.0 0.0 4.5 0.0 0.78 0.0

Floor 1 Humid 54 540 215.3 1.1 1.1 0.0 5.0 0.0 0.00 0.0

Floor 1 IT Hall 140 1,400 0.0 1.0 0.4 0.0 7.0 0.0 0.00 0.0

Floor 1 IT Room 112 1,120 215.3 1.1 1.1 0.0 10.4 0.0 0.00 0.0
55

Building Type/Zone

Area

ft2

Vol.

ft3

ft2/

person

1989

Lights

Wft2

2004

Lights

Wft2

Elec.

Proc.

W/ft2

Gas 

Proc. 

W/ft2

Vent. 

cfm

Exhst 

cfm

Infil. 

ACH 

SWH 

gal/h

Floor 1 Lobby 622 6,220 35.9 1.3 1.1 0.0 260.0 0.0 0.13 0.0

Floor 1 Lobby Hall 240 2,400 0.0 1.0 0.4 0.0 12.0 0.0 0.00 0.0

Floor 1 Lobby Toilet 54 540 0.0 0.9 0.4 0.0 108.0 90.0 0.40 0.0

Floor 1 Locker Room 660 6,600 71.8 0.8 3.0 0.0 138.0 0.0 0.12 0.0

Floor 1 Locker Room Hall 496 4,960 0.0 1.0 0.4 0.0 24.8 0.0 0.00 0.0

Floor 1 Lounge 360 3,600 71.8 0.8 3.0 0.0 75.3 0.0 0.00 0.0

Floor 1 Med Gas 56 560 0.0 0.9 0.1 0.0 8.4 0.0 0.96 0.0

Floor 1 MRI Control Room 168 1,680 53.8 0.4 10.0 0.0 50.4 168.0 0.11 1.0

Floor 1 MRI Hall 147 1,470 0.0 1.0 0.4 0.0 7.3 0.0 0.00 0.0

Floor 1 MRI Room 440 4,400 53.8 0.4 10.0 0.0 132.0 440.0 0.00 1.0

Floor 1 MRI Toilet 54 540 0.0 0.9 0.4 0.0 108.0 90.0 0.40 0.0

Floor 1 Nourishment 182 1,820 53.8 1.0 2.0 0.0 67.6 0.0 0.00 0.0

Floor 1 Nurse Hall 496 4,960 0.0 1.0 0.4 0.0 24.8 0.0 0.00 0.0

Floor 1 Nurse Janitor 54 540 0.0 0.9 0.1 0.0 8.1 0.0 0.00 0.0

Floor 1 Nurse Station 261 2,610 53.8 1.0 2.0 0.0 97.0 0.0 0.00 0.0

Floor 1 Nurse Toilet 54 540 0.0 0.9 0.4 0.0 108.0 90.0 0.00 0.0

Floor 1 Office 483 4,830 215.3 1.1 1.1 0.0 44.9 0.0 0.00 0.0

Floor 1 Operating Room 1 460 4,600 53.8 2.2 4.0 7.0 230.0 0.0 0.33 6.0

Floor 1 Operating Room 2 480 4,800 53.8 2.2 4.0 7.0 240.0 0.0 0.18 6.0

Floor 1 Operating Room 3 476 4,760 53.8 2.2 4.0 7.0 238.0 0.0 0.00 6.0

Floor 1 PACU 108 1,080 53.8 0.8 3.0 0.0 36.0 0.0 0.00 1.0

Floor 1 Pre-Op Hall 528 5,280 0.0 1.0 0.4 0.0 26.4 0.0 0.00 0.0

Floor 1 Pre-Op Room 1 189 1,890 107.6 0.7 2.0 0.0 63.0 0.0 0.08 1.0

Floor 1 Pre-Op Room 2 338 3,380 107.6 0.7 2.0 0.0 112.7 0.0 0.00 1.0

Floor 1 Pre-Op Toilet 54 540 0.0 0.9 0.4 0.0 108.0 90.0 0.40 0.0

Floor 1 Procedure Room 285 2,850 53.8 2.7 3.0 0.0 142.5 0.0 0.24 1.0

Floor 1 Reception 509 5,090 35.9 1.3 1.1 0.0 212.8 0.0 0.09 0.0

Floor 1 Reception Hall 128 1,280 0.0 1.0 0.4 0.0 6.4 0.0 0.00 0.0

Floor 1 Recovery Room 540 5,400 53.8 0.8 3.0 0.0 180.0 0.0 0.30 1.0

Floor 1 Scheduling 119 1,190 215.3 1.1 1.1 0.0 11.1 0.0 0.21 0.0

Floor 1 Scrub 84 840 0.0 1.0 0.4 0.0 4.2 0.0 0.00 0.0

Floor 1 Soil 126 1,260 53.8 1.2 2.0 0.0 189.0 210.0 0.00 0.0

Floor 1 Soil Hold 56 560 53.8 1.2 2.0 0.0 84.0 93.3 0.00 0.0

Floor 1 Soil Work 180 1,800 53.8 1.2 2.0 0.0 270.0 300.0 0.00 0.0

Floor 1 Step Down 300 3,000 53.8 0.8 3.0 0.0 100.0 0.0 0.44 1.0

Floor 1 Sterile Hall 616 6,160 0.0 1.0 0.4 0.0 30.8 0.0 0.05 0.0

Floor 1 Sterile Storage 396 3,960 0.0 0.9 0.1 0.0 59.4 0.0 0.00 0.0

Floor 1 Storage 920 9,200 0.0 0.9 0.1 0.0 138.0 0.0 0.24 0.0

Floor 1 Sub-Sterile 196 1,960 0.0 1.0 0.4 0.0 9.8 0.0 0.26 0.0

Floor 1 Utility Hall 256 2,560 0.0 1.0 0.4 0.0 12.8 0.0 0.22 0.0

Floor 1 Utility Janitor 42 420 0.0 0.9 0.1 0.0 6.3 0.0 0.00 0.0

Floor 1 Utility Room 360 3,600 0.0 0.9 0.1 0.0 54.0 0.0 0.18 0.0

Floor 1 Vestibule 72 720 0.0 1.0 0.4 0.0 3.6 0.0 0.40 0.0

Floor 2 Conference 336 3,360 21.5 1.3 1.0 0.0 312.2 0.0 0.43 0.0

Floor 2 Conference Toilet 64 640 0.0 0.9 0.4 0.0 128.0 106.7 0.00 0.0

Floor 2 Dictation 70 700 215.3 1.1 1.1 0.0 6.5 0.0 0.00 0.0

Floor 2 Exam 1 360 3,600 53.8 1.5 1.1 0.0 108.0 0.0 0.42 0.0

Floor 2 Exam 2 540 5,400 53.8 1.5 1.1 0.0 162.0 0.0 0.12 0.0

Floor 2 Exam 3 720 7,200 53.8 1.5 1.1 0.0 216.0 0.0 0.12 0.0

Floor 2 Exam 4 84 840 53.8 1.5 1.1 0.0 25.2 0.0 0.30 0.0

Floor 2 Exam 5 350 3,500 53.8 1.5 1.1 0.0 105.0 0.0 0.26 0.0

Floor 2 Exam 6 225 2,250 53.8 1.5 1.1 0.0 67.5 0.0 0.24 0.0

Floor 2 Exam 7 792 7,920 53.8 1.5 1.1 0.0 237.6 0.0 0.11 0.0

Floor 2 Exam 8 270 2,700 53.8 1.5 1.1 0.0 81.0 0.0 0.24 0.0

Floor 2 Exam 9 396 3,960 53.8 1.5 1.1 0.0 118.8 0.0 0.11 0.0

Floor 2 Exam Hall 1 180 1,800 0.0 1.0 0.4 0.0 9.0 0.0 0.12 0.0
56

Building Type/Zone

Area

ft2

Vol.

ft3

ft2/

person

1989

Lights

Wft2

2004

Lights

Wft2

Elec.

Proc.

W/ft2

Gas 

Proc. 

W/ft2

Vent. 

cfm

Exhst 

cfm

Infil. 

ACH 

SWH 

gal/h

Floor 2 Exam Hall 2 180 1,800 0.0 1.0 0.4 0.0 9.0 0.0 0.12 0.0

Floor 2 Exam Hall 3 180 1,800 0.0 1.0 0.4 0.0 9.0 0.0 0.12 0.0

Floor 2 Exam Hall 4 198 1,980 0.0 1.0 0.4 0.0 9.9 0.0 0.11 0.0

Floor 2 Exam Hall 5 198 1,980 0.0 1.0 0.4 0.0 9.9 0.0 0.11 0.0

Floor 2 Exam Hall 6 198 1,980 0.0 1.0 0.4 0.0 9.9 0.0 0.11 0.0

Floor 2 Janitor 63 630 0.0 0.9 0.1 0.0 9.4 0.0 0.91 0.0

Floor 2 Lounge 80 800 71.8 0.8 3.0 0.0 16.7 0.0 0.00 0.0

Floor 2 Nurse Station 1 150 1,500 53.8 1.0 2.0 0.0 55.7 0.0 0.00 0.0

Floor 2 Nurse Station 2 180 1,800 53.8 1.0 2.0 0.0 66.9 0.0 0.00 0.0

Floor 2 Office 560 5,600 215.3 1.1 1.1 0.0 52.0 0.0 0.26 0.0

Floor 2 Office Hall 444 4,440 0.0 1.0 0.4 0.0 22.2 0.0 0.00 0.0

Floor 2 Reception 984 9,840 35.9 1.3 1.1 0.0 411.4 0.0 0.18 0.0

Floor 2 Reception Hall 564 5,640 0.0 1.0 0.4 0.0 28.2 0.0 0.60 0.0

Floor 2 Reception Toilet 126 1,260 0.0 0.9 0.4 0.0 252.0 210.0 0.00 0.0

Floor 2 Scheduling 1 324 3,240 215.3 1.1 1.1 0.0 30.1 0.0 0.00 0.0

Floor 2 Scheduling 2 342 3,420 215.3 1.1 1.1 0.0 31.8 0.0 0.00 0.0

Floor 2 Storage 1 56 560 0.0 0.9 0.1 0.0 8.4 0.0 0.00 0.0

Floor 2 Storage 2 120 1,200 0.0 0.9 0.1 0.0 18.0 0.0 0.00 0.0

Floor 2 Storage 3 144 1,440 0.0 0.9 0.1 0.0 21.6 0.0 0.00 0.0

Floor 2 Utility 126 1,260 0.0 0.9 0.1 0.0 18.9 0.0 0.26 0.0

Floor 2 Work 1,690 16,900 215.3 1.1 1.1 0.0 157.0 0.0 0.05 0.0

Floor 2 Work Hall 834 8,340 0.0 1.0 0.4 0.0 41.7 0.0 0.03 0.0

Floor 2 Work Toilet 54 540 0.0 0.9 0.4 0.0 108.0 0.0 0.40 0.0

Floor 2 X-Ray 900 9,000 53.8 0.4 10.0 0.0 270.0 0.0 0.00 1.0

Floor 3 Dressing Room 42 420 215.3 1.1 1.1 0.0 3.9 0.0 0.00 0.0

Floor 3 Elevator Hall 370 3,700 0.0 1.0 0.4 0.0 18.5 0.0 0.04 0.0

Floor 3 Humid 108 1,080 215.3 1.1 1.1 0.0 10.0 0.0 0.00 0.0

Floor 3 Janitor 63 630 0.0 0.9 0.1 0.0 9.4 0.0 0.91 0.0

Floor 3 Locker 120 1,200 71.8 0.8 3.0 0.0 25.1 0.0 0.00 0.0

Floor 3 Lounge 759 7,590 71.8 0.8 3.0 0.0 158.7 0.0 0.11 0.0

Floor 3 Lounge Toilet 192 1,920 0.0 0.9 0.4 0.0 384.0 320.0 0.22 0.0

Floor 3 Mechanical 350 3,500 0.0 1.5 5.0 0.0 17.5 0.0 0.26 0.0

Floor 3 Mechanical Hall 300 3,000 0.0 1.0 0.4 0.0 15.0 0.0 0.00 0.0

Floor 3 Office 3,036 30,360 215.3 1.1 1.1 0.0 282.1 0.0 0.09 0.0

Floor 3 Office Hall 834 8,340 0.0 1.0 0.4 0.0 41.7 0.0 0.03 0.0

Floor 3 Office Toilet 54 540 0.0 0.9 0.4 0.0 108.0 90.0 0.40 0.0

Floor 3 Physical Therapy 1 1,300 13,000 53.8 0.9 1.5 0.0 362.3 0.0 0.23 1.0

Floor 3 Physical Therapy 2 592 5,920 53.8 0.9 1.5 0.0 165.0 0.0 0.00 1.0

Floor 3 Physical Therapy Toilet 84 840 0.0 0.9 0.4 0.0 168.0 140.0 0.00 0.0

Floor 3 Storage 1 108 1,080 0.0 0.9 0.1 0.0 16.2 0.0 0.00 0.0

Floor 3 Storage 2 84 840 0.0 0.9 0.1 0.0 12.6 0.0 0.00 0.0

Floor 3 Treatment 476 4,760 53.8 1.5 1.1 0.0 142.8 0.0 0.00 0.0

Floor 3 Undeveloped 1 2,268 22,680 215.3 1.1 1.1 0.0 340.2 0.0 0.11 0.0

Floor 3 Undeveloped 2 1,152 11,520 215.3 1.1 1.1 0.0 172.8 0.0 0.17 0.0

Floor 3 Utility 216 2,160 0.0 0.9 0.1 0.0 32.4 0.0 0.00 0.0

Floor 3 Work 574 5,740 215.3 1.1 1.1 0.0 53.3 0.0 0.26 0.0

NE Stair 168 5,040 0.0 1.0 0.4 0.0 8.4 0.0 0.74 0.0

NW Elevator 140 4,200 0.0 1.0 0.4 0.0 7.0 0.0 0.69 0.0

NW Stair 192 5,760 0.0 1.0 0.4 0.0 9.6 0.0 0.74 0.0

SW Stair 96 2,880 0.0 1.0 0.4 0.0 4.8 0.0 0.74 0.0

Retail 24,692 494,171

Back_Space 4,089 81,836 300.0 1.17 0.8 0.8 0.0 613.4 0.0 0.37 0.0

Core_Retail 17,227 344,775 66.7 3.37 1.7 0.3 0.0 5168.2 0.0 0.22 0.0

Point_of_Sale 1,623 32,487 66.7 3.37 1.7 2.0 0.0 487.0 0.0 0.40 0.0

Front_Retail 1,623 32,487 66.7 3.37 1.7 0.3 0.0 487.0 0.0 0.40 0.0

Front_Entry 129 2,585 66.7 3.37 1.1 0.0 0.0 0.0 0.0 0.54 0.0
57

Building Type/Zone

Area

ft2

Vol.

ft3

ft2/

person

1989

Lights

Wft2

2004

Lights

Wft2

Elec.

Proc.

W/ft2

Gas 

Proc. 

W/ft2

Vent. 

cfm

Exhst 

cfm

Infil. 

ACH 

SWH 

gal/h

Primary Education 73,959 970,588

CORNER_CLASS_1_POD_1_Z

N_1_FLR_1 1,066 13,985 43.1 2.00 1.4 1.4 0.0 371.3 0.0 0.49 0.0

MULT_CLASS_1_POD_1_ZN_1

_FLR_1 5,134 67,380 43.1 2.00 1.4 1.4 0.0 1788.8 0.0 0.39 0.0

CORRIDOR_POD_1_ZN_1_FL

R_1 2,067 27,122 107.6 2.00 0.5 0.4 0.0 206.7 0.0 0.29 0.0

CORNER_CLASS_2_POD_1_Z

N_1_FLR_1 1,066 13,985 43.1 2.00 1.4 1.4 0.0 371.3 0.0 0.49 0.0

MULT_CLASS_2_POD_1_ZN_1

_FLR_1 5,134 67,380 43.1 2.00 1.4 1.4 0.0 1788.8 0.0 0.39 0.0

CORNER_CLASS_1_POD_2_Z

N_1_FLR_1 1,066 13,985 43.1 2.00 1.4 1.4 0.0 371.3 0.0 0.49 0.0

MULT_CLASS_1_POD_2_ZN_1

_FLR_1 5,134 67,380 43.1 2.00 1.4 1.4 0.0 1788.8 0.0 0.39 0.0

CORRIDOR_POD_2_ZN_1_FL

R_1 2,067 27,122 107.6 0.90 0.5 0.4 0.0 206.7 0.0 0.29 0.0

CORNER_CLASS_2_POD_2_Z

N_1_FLR_1 1,066 13,985 43.1 2.00 1.4 1.4 0.0 371.3 0.0 0.49 0.0

MULT_CLASS_2_POD_2_ZN_1

_FLR_1 5,134 67,380 43.1 2.00 1.4 1.4 0.0 1788.8 0.0 0.39 0.0

CORNER_CLASS_1_POD_3_Z

N_1_FLR_1 1,066 13,985 43.1 2.00 1.4 1.4 0.0 371.3 0.0 0.49 0.0

MULT_CLASS_1_POD_3_ZN_1

_FLR_1 5,134 67,380 43.1 2.00 1.4 1.4 0.0 1788.8 0.0 0.39 0.0

CORRIDOR_POD_3_ZN_1_FL

R_1 2,067 27,122 107.6 0.90 0.5 0.4 0.0 206.7 0.0 0.29 0.0

CORNER_CLASS_2_POD_3_Z

N_1_FLR_1 1,066 13,985 43.1 2.00 1.4 1.4 0.0 371.3 0.0 0.49 0.0

MULT_CLASS_2_POD_3_ZN_1

_FLR_1 3,391 44,496 43.1 2.00 1.4 0.7 0.0 1181.3 0.0 0.39 0.0

COMPUTER_CLASS_ZN_1_FL

R_1 1,744 22,884 35.8 2.00 1.4 1.9 0.0 729.7 0.0 0.39 0.0

MAIN_CORRIDOR_ZN_1_FLR_

1 5,877 77,127 0.0 1.04 0.5 0.4 0.0 587.7 0.0 0.29 0.0

LOBBY_ZN_1_FLR_1 1,841 24,155 0.0 1.14 1.3 0.4 0.0 184.1 0.0 0.39 0.0

MECH_ZN_1_FLR_1 2,713 35,597 1076.4 0.77 1.5 0.9 0.0 135.6 0.0 0.27 0.0

BATH_ZN_1_FLR_1 2,045 26,839 1076.4 0.90 0.9 0.4 0.0 600.0 600.0 0.33 56.5

OFFICES_ZN_1_FLR_1 4,747 62,295 215.3 1.89 1.1 1.0 0.0 441.0 0.0 0.38 0.0

GYM_ZN_1_FLR_1 3,843 50,429 35.8 1.07 1.4 0.5 0.0 2144.1 0.0 0.32 0.0

KITCHEN_ZN_1_FLR_1 1,808 23,731 71.8 1.60 1.2 17.7 88.7 377.8 3300.0 0.32 100.0

CAFETERIA_ZN_1_FLR_1 3,391 44,496 15.0 1.40 1.4 2.4 0.0 4520.8 0.0 0.40 0.0

LIBRARY_MEDIA_CENTER_Z

N_1_FLR_1 4,295 56,362 46.8 2.11 1.3 1.4 0.0 1375.9 0.0 0.38 0.0

Secondary Education 210,886 3,362,522

CORNER_CLASS_1_POD_1_Z

N_1_FLR_1 1,066 13,985 43.1 2.00 1.4 0.9 0.0 371.3 0.0 0.22 0.0

CORNER_CLASS_1_POD_1_Z

N_1_FLR_2 1,066 13,985 43.1 2.00 1.4 0.9 0.0 371.3 0.0 0.49 0.0

MULT_CLASS_1_POD_1_ZN_1

_FLR_1 5,134 67,380 43.1 2.00 1.4 0.9 0.0 1788.8 0.0 0.12 0.0

MULT_CLASS_1_POD_1_ZN_1

_FLR_2 5,134 67,380 43.1 2.00 1.4 0.9 0.0 1788.8 0.0 0.39 0.0

CORRIDOR_POD_1_ZN_1_FL

R_1 3,444 45,203 107.6 0.86 0.5 0.4 0.0 344.4 0.0 0.02 0.0

CORRIDOR_POD_1_ZN_1_FL

R_2 3,444 45,203 107.6 0.86 0.5 0.4 0.0 344.4 0.0 0.29 0.0

CORNER_CLASS_2_POD_1_Z

N_1_FLR_1 1,066 13,985 43.1 2.00 1.4 0.9 0.0 371.3 0.0 0.22 0.0

CORNER_CLASS_2_POD_1_Z 1,066 13,985 43.1 2.00 1.4 0.9 0.0 371.3 0.0 0.49 0.0
58

Building Type/Zone

Area

ft2

Vol.

ft3

ft2/

person

1989

Lights

Wft2

2004

Lights

Wft2

Elec.

Proc.

W/ft2

Gas 

Proc. 

W/ft2

Vent. 

cfm

Exhst 

cfm

Infil. 

ACH 

SWH 

gal/h

N_1_FLR_2 

MULT_CLASS_2_POD_1_ZN_1

_FLR_1 5,134 67,380 43.1 2.00 1.4 0.9 0.0 1788.8 0.0 0.12 0.0

MULT_CLASS_2_POD_1_ZN_1

_FLR_2 5,134 67,380 43.1 2.00 1.4 0.9 0.0 1788.8 0.0 0.39 0.0

CORNER_CLASS_1_POD_2_Z

N_1_FLR_1 1,066 13,985 43.1 2.00 1.4 0.9 0.0 371.3 0.0 0.22 0.0

CORNER_CLASS_1_POD_2_Z

N_1_FLR_2 1,066 13,985 43.1 2.00 1.4 0.9 0.0 371.3 0.0 0.49 0.0

MULT_CLASS_1_POD_2_ZN_1

_FLR_1 5,134 67,380 43.1 2.00 1.4 0.9 0.0 1788.8 0.0 0.12 0.0

MULT_CLASS_1_POD_2_ZN_1

_FLR_2 5,134 67,380 43.1 2.00 1.4 0.9 0.0 1788.8 0.0 0.39 0.0

CORRIDOR_POD_2_ZN_1_FL

R_1 3,444 45,203 107.6 0.86 0.5 0.4 0.0 344.4 0.0 0.02 0.0

CORRIDOR_POD_2_ZN_1_FL

R_2 3,444 45,203 107.6 0.86 0.5 0.4 0.0 344.4 0.0 0.29 0.0

CORNER_CLASS_2_POD_2_Z

N_1_FLR_1 1,066 13,985 43.1 2.00 1.4 0.9 0.0 371.3 0.0 0.22 0.0

CORNER_CLASS_2_POD_2_Z

N_1_FLR_2 1,066 13,985 43.1 2.00 1.4 0.9 0.0 371.3 0.0 0.49 0.0

MULT_CLASS_2_POD_2_ZN_1

_FLR_1 5,134 67,380 43.1 2.00 1.4 0.9 0.0 1788.8 0.0 0.12 0.0

MULT_CLASS_2_POD_2_ZN_1

_FLR_2 5,134 67,380 43.1 2.00 1.4 0.9 0.0 1788.8 0.0 0.39 0.0

CORNER_CLASS_1_POD_3_Z

N_1_FLR_1 1,066 13,985 43.1 2.00 1.4 0.9 0.0 371.3 0.0 0.22 0.0

CORNER_CLASS_1_POD_3_Z

N_1_FLR_2 1,066 13,985 43.1 2.00 1.4 0.9 0.0 371.3 0.0 0.49 0.0

MULT_CLASS_1_POD_3_ZN_1

_FLR_1 5,134 67,380 43.1 2.00 1.4 0.9 0.0 1788.8 0.0 0.12 0.0

MULT_CLASS_1_POD_3_ZN_1

_FLR_2 5,134 67,380 43.1 2.00 1.4 1.9 0.0 1788.8 0.0 0.39 0.0

CORRIDOR_POD_3_ZN_1_FL

R_1 3,444 45,203 107.6 0.86 0.5 0.4 0.0 344.4 0.0 0.02 0.0

CORRIDOR_POD_3_ZN_1_FL

R_2 3,444 45,203 107.6 0.86 0.5 0.4 0.0 344.4 0.0 0.29 0.0

CORNER_CLASS_2_POD_3_Z

N_1_FLR_1 1,066 13,985 43.1 2.00 1.4 0.9 0.0 371.3 0.0 0.22 0.0

CORNER_CLASS_2_POD_3_Z

N_1_FLR_2 1,066 13,985 43.1 2.00 1.4 0.9 0.0 371.3 0.0 0.49 0.0

MULT_CLASS_2_POD_3_ZN_1

_FLR_1 5,134 67,380 43.1 2.00 1.4 0.9 0.0 1788.8 0.0 0.12 0.0

MULT_CLASS_2_POD_3_ZN_1

_FLR_2 5,134 67,380 43.1 2.00 1.4 1.9 0.0 1788.8 0.0 0.39 0.0

MAIN_CORRIDOR_ZN_1_FLR_

1 12,271 161,035 0.0 1.00 0.5 0.4 0.0 1227.1 0.0 0.05 0.0

MAIN_CORRIDOR_ZN_1_FLR_

2 12,271 161,035 0.0 1.00 0.5 0.4 0.0 1227.1 0.0 0.32 0.0

LOBBY_ZN_1_FLR_1 2,260 29,664 0.0 1.12 1.3 0.4 0.0 226.0 0.0 0.08 0.0

LOBBY_ZN_1_FLR_2 2,260 29,664 0.0 1.12 1.3 0.4 0.0 226.0 0.0 0.35 0.0

BATHROOMS_ZN_1_FLR_1 2,260 29,664 107.6 0.89 0.9 0.4 0.0 600.0 0.0 0.15 52.2

BATHROOMS_ZN_1_FLR_2 2,260 29,664 107.6 0.89 0.9 0.4 0.0 600.0 0.0 0.42 52.2

OFFICES_ZN_1_FLR_1 5,726 75,150 215.3 1.87 1.1 1.0 0.0 532.0 0.0 0.11 0.0

OFFICES_ZN_1_FLR_2 5,726 75,150 215.3 1.87 1.1 1.0 0.0 532.0 0.0 0.38 0.0

GYM_ZN_1_FLR_1 21,269 558,254 10.8 1.06 1.4 0.5 0.0 39520.0 0.0 0.14 189.5

AUX_GYM_ZN_1_FLR_1 13,433 352,582 35.8 1.10 1.4 0.5 0.0 7495.5 0.0 0.20 0.0

AUDITORIUM_ZN_1_FLR_1 10,635 279,127 10.8 1.12 0.9 0.5 0.0 14820.0 0.0 0.21 0.0

KITCHEN_ZN_1_FLR_1 2,325 30,512 71.8 1.56 1.2 20.7 104.0 485.8 4000.0 0.05 133.0

LIBRARY_MEDIA_CENTER_Z 9,042 118,657 46.8 0.00 1.3 0.9 0.0 2896.6 0.0 0.35 0.0
59

Building Type/Zone

Area

ft2

Vol.

ft3

ft2/

person

1989

Lights

Wft2

2004

Lights

Wft2

Elec.

Proc.

W/ft2

Gas 

Proc. 

W/ft2

Vent. 

cfm

Exhst 

cfm

Infil. 

ACH 

SWH 

gal/h

N_1_FLR_2 

CAFETERIA_ZN_1_FLR_1 6,717 88,145 15.0 1.34 1.4 1.8 0.0 8955.6 0.0 0.09 0.0

MECH_ZN_1_FLR_1 3,681 48,310 1076.4 0.75 1.5 0.4 0.0 184.1 0.0 0.00 0.0

MECH_ZN_1_FLR_2 3,681 48,310 1076.4 0.75 1.5 0.4 0.0 184.1 0.0 0.00 0.0

Full Service Restaurant 5,502 55,035

Dining 4,001 40,025 15.0 2.54 2.1 5.6 0.0 5335.3 0.0 0.52 0.0

Kitchen 1,501 15,009 200.0 1.52 1.2 35.0 111.3 112.5 4000.0 0.63 133.0

Attic 5,502 30,239 0.0 0.00 0.0 0.0 0.0 0.0 0.0 1.00 0.0

Supermarket 45,002 900,272

Office 956 19,131 200.0 1.98 1.1 0.8 0.0 95.6 0.0 0.41 0.0

DryStorage 6,694 133,914 300.0 1.11 0.8 0.8 0.0 1004.1 0.0 0.32 0.0

Deli 2,419 48,390 125.0 2.78 1.7 5.0 2.5 725.7 0.0 0.29 5.0

Sales 25,025 500,642 125.0 2.78 1.7 0.5 0.0 7507.6 0.0 0.20 0.0

Produce 7,657 153,181 125.0 2.78 1.7 0.5 0.0 2297.1 0.0 0.27 0.0

Bakery 2,250 45,014 125.0 2.78 1.7 5.0 2.5 675.0 2500.0 0.34 5.0

Small Hotel 43,202 410,418

REARSTAIRSFLR1 216 2,377 0.0 0.92 0.6 0.0 0.0 0.0 0.0 0.58 0.0

CORRIDORFLR1 1,620 17,820 0.0 0.88 0.5 0.0 0.0 0.0 0.0 0.07 0.0

REARSTORAGEFLR1 216 2,377 0.0 0.46 0.8 0.0 0.0 81.0 0.0 0.58 0.0

FRONTLOUNGEFLR1 1,755 19,307 33.2 1.31 1.1 1.4 0.0 0.0 0.0 0.19 0.0

RESTROOMFLR1 351 3,861 351.0 1.10 0.9 1.0 0.0 794.1 0.0 0.13 0.0

MEETINGROOMFLR1 864 9,505 20.1 2.13 1.3 1.2 0.0 0.0 400.0 0.13 0.0

MECHANICALROOMFLR1 351 3,861 0.0 0.96 1.5 0.0 0.0 858.5 0.0 0.13 0.0

GUESTROOM101 351 3,861 234.0 1.92 1.1 1.3 0.0 17.6 0.0 0.13 1.8

GUESTROOM102 351 3,861 234.0 1.92 1.1 1.3 0.0 30.0 0.0 0.13 1.8

GUESTROOM103 351 3,861 234.0 1.92 1.1 1.3 0.0 30.0 0.0 0.13 1.8

GUESTROOM104 351 3,861 234.0 1.92 1.1 1.3 0.0 30.0 0.0 0.13 1.8

GUESTROOM105 351 3,861 234.0 1.92 1.1 1.3 0.0 30.0 0.0 0.13 1.8

EMPLOYEELOUNGEFLR1 351 3,861 31.9 1.65 1.2 7.2 0.0 30.0 0.0 0.13 0.0

LAUNDRYROOMFLR1 1,053 11,583 95.7 1.04 0.6 2.0 17.1 165.3 0.0 0.13 67.5

ELEVATORCOREFLR1 162 1,782 0.0 0.00 0.0 11.9 0.0 275.1 0.0 0.13 0.0

EXERCISECENTERFLR1 351 3,861 31.9 1.37 0.9 1.1 0.0 162.0 0.0 0.13 0.0

FRONTOFFICEFLR1 1,404 15,444 140.4 2.01 1.1 1.2 0.0 220.3 0.0 0.13 0.0

FRONTSTAIRSFLR1 216 2,376 0.0 0.92 0.6 0.0 0.0 200.1 0.0 0.58 0.0

FRONTSTORAGEFLR1 135 1,485 0.0 0.53 0.8 0.0 0.0 0.0 0.0 0.13 0.0

REARSTAIRSFLR2 216 1,944 0.0 0.82 0.6 0.0 0.0 0.0 0.0 0.58 0.0

CORRIDORFLR2 1,350 12,150 0.0 0.86 0.5 0.0 0.0 0.0 0.0 0.06 0.0

REARSTORAGEFLR2 216 1,945 0.0 0.41 0.8 0.0 0.0 67.5 0.0 0.58 0.0

GUESTROOM201 351 3,159 234.0 1.74 1.1 1.3 0.0 0.0 0.0 0.41 1.8

GUESTROOM202_205 1,404 12,637 234.0 1.74 1.1 1.3 0.0 30.0 0.0 0.13 7.0

GUESTROOM206_208 1,134 10,207 252.0 1.74 1.1 1.3 0.0 120.0 0.0 0.13 5.3

GUESTROOM209_212 1,404 12,637 234.0 1.74 1.1 1.3 0.0 90.0 0.0 0.13 7.0

GUESTROOM213 351 3,159 234.0 1.74 1.1 1.3 0.0 120.0 0.0 0.13 1.8

GUESTROOM214 351 3,159 234.0 1.74 1.1 1.3 0.0 30.0 0.0 0.13 1.8

GUESTROOM215_218 1,404 12,636 234.0 1.74 1.1 1.3 0.0 30.0 0.0 0.13 7.0

ELEVATORCOREFLR2 162 1,458 0.0 0.00 0.0 0.0 0.0 120.0 0.0 0.13 0.0

GUESTROOM219 351 3,159 234.0 1.74 1.1 1.3 0.0 0.0 0.0 0.13 1.8

GUESTROOM220_223 1,404 12,636 234.0 1.74 1.1 1.3 0.0 30.0 0.0 0.13 7.0

GUESTROOM224 351 3,159 234.0 1.74 1.1 1.3 0.0 120.0 0.0 0.13 1.8

FRONTSTORAGEFLR2 135 1,215 0.0 0.45 0.8 0.0 0.0 30.0 0.0 0.13 0.0

FRONTSTAIRSFLR2 216 1,944 0.0 0.82 0.6 0.0 0.0 0.0 0.0 0.58 0.0

REARSTAIRSFLR3 216 1,944 0.0 0.82 0.6 0.0 0.0 0.0 0.0 0.58 0.0

CORRIDORFLR3 1,350 12,150 0.0 0.86 0.5 0.0 0.0 0.0 0.0 0.06 0.0

REARSTORAGEFLR3 216 1,945 0.0 0.41 0.8 0.0 0.0 67.5 0.0 0.58 0.0

GUESTROOM301 351 3,159 234.0 1.74 1.1 1.3 0.0 0.0 0.0 0.41 1.8

GUESTROOM302_305 1,404 12,637 234.0 1.74 1.1 1.3 0.0 30.0 0.0 0.13 7.0
60

Building Type/Zone

Area

ft2

Vol.

ft3

ft2/

person

1989

Lights

Wft2

2004

Lights

Wft2

Elec.

Proc.

W/ft2

Gas 

Proc. 

W/ft2

Vent. 

cfm

Exhst 

cfm

Infil. 

ACH 

SWH 

gal/h

GUESTROOM306_308 1,134 10,207 252.0 1.74 1.1 1.3 0.0 120.0 0.0 0.13 5.3

GUESTROOM309_312 1,404 12,637 234.0 1.74 1.1 1.3 0.0 90.0 0.0 0.13 7.0

GUESTROOM313 351 3,159 234.0 1.74 1.1 1.3 0.0 120.0 0.0 0.13 1.8

GUESTROOM314 351 3,159 234.0 1.74 1.1 1.3 0.0 30.0 0.0 0.13 1.8

GUESTROOM315_318 1,404 12,636 234.0 1.74 1.1 1.3 0.0 30.0 0.0 0.13 7.0

ELEVATORCOREFLR3 162 1,458 0.0 0.00 0.0 0.0 0.0 120.0 0.0 0.13 0.0

GUESTROOM319 351 3,159 234.0 1.74 1.1 1.3 0.0 0.0 0.0 0.13 1.8

GUESTROOM320_323 1,404 12,636 234.0 1.74 1.1 1.3 0.0 30.0 0.0 0.13 7.0

GUESTROOM324 351 3,159 234.0 1.74 1.1 1.3 0.0 120.0 0.0 0.13 1.8

FRONTSTORAGEFLR3 135 1,215 0.0 0.45 0.8 0.0 0.0 30.0 0.0 0.13 0.0

FRONTSTAIRSFLR3 216 1,944 0.0 0.82 0.6 0.0 0.0 0.0 0.0 0.58 0.0

REARSTAIRSFLR4 216 1,944 0.0 0.41 0.6 0.0 0.0 0.0 0.0 0.98 0.0

CORRIDORFLR4 1,350 12,150 0.0 0.86 0.5 0.0 0.0 0.0 0.0 0.45 0.0

REARSTORAGEFLR4 216 1,945 0.0 0.41 0.8 0.0 0.0 67.5 0.0 0.98 0.0

GUESTROOM401 351 3,159 234.0 1.74 1.1 1.3 0.0 0.0 0.0 0.80 1.8

GUESTROOM402_405 1,404 12,637 234.0 1.74 1.1 1.3 0.0 30.0 0.0 0.53 7.0

GUESTROOM406_408 1,134 10,207 252.0 1.74 1.1 1.3 0.0 120.0 0.0 0.53 5.3

GUESTROOM409_412 1,404 12,637 234.0 1.74 1.1 1.3 0.0 90.0 0.0 0.53 7.0

GUESTROOM413 351 3,159 234.0 1.74 1.1 1.3 0.0 120.0 0.0 0.53 1.8

GUESTROOM414 351 3,159 234.0 1.74 1.1 1.3 0.0 30.0 0.0 0.53 1.8

GUESTROOM415_418 1,404 12,636 234.0 1.74 1.1 1.3 0.0 30.0 0.0 0.53 7.0

ELEVATORCOREFLR4 162 1,458 0.0 0.00 0.0 0.0 0.0 120.0 0.0 0.53 0.0

GUESTROOM419 351 3,159 234.0 1.74 1.1 1.3 0.0 0.0 0.0 0.53 1.8

GUESTROOM420_423 1,404 12,636 234.0 1.74 1.1 1.3 0.0 30.0 0.0 0.53 7.0

GUESTROOM424 351 3,159 234.0 1.74 1.1 1.3 0.0 120.0 0.0 0.53 1.8

FRONTSTORAGEFLR4 135 1,215 0.0 0.45 0.8 0.0 0.0 30.0 0.0 0.53 0.0

FRONTSTAIRSFLR4 216 1,944 0.0 0.82 0.6 0.0 0.0 0.0 0.0 0.98 0.0

Small Office 5,502 55,056

Core_ZN 1,611 16,120 200.0 1.81 1.0 0.8 0.0 161.1 0.0 0.00 3.0

Perimeter_ZN_1 1,221 12,220 200.0 1.81 1.0 0.8 0.0 122.1 0.0 0.62 0.0

Perimeter_ZN_2 724 7,249 200.0 1.81 1.0 0.8 0.0 72.4 0.0 0.66 0.0

Perimeter_ZN_3 1,221 12,220 200.0 1.81 1.0 0.8 0.0 122.1 0.0 0.62 0.0

Perimeter_ZN_4 724 7,249 200.0 1.81 1.0 0.8 0.0 72.4 0.0 0.66 0.0

Attic 6,114 25,433 0.0 0.00 0.0 0.0 0.0 0.0 0.0 1.00 0.0

Strip Mall 22,500 382,500

LGStore1 3,750 63,750 66.7 5.60 2.2 0.4 0.0 1125.0 0.0 0.38 0.0

SMStore1 1,875 31,875 66.7 5.60 2.2 0.4 0.0 562.5 0.0 0.31 0.0

SMStore2 1,875 31,875 66.7 3.30 1.7 0.4 0.0 562.5 0.0 0.31 0.0

SMStore3 1,875 31,875 66.7 3.30 1.7 0.4 0.0 562.5 0.0 0.31 0.0

SMStore4 1,875 31,875 66.7 3.30 1.7 0.4 0.0 562.5 0.0 0.31 0.0

LGStore2 3,750 63,750 66.7 2.70 1.3 0.4 0.0 1125.0 0.0 0.31 0.0

SMStore5 1,875 31,875 66.7 2.70 1.3 0.4 0.0 562.5 0.0 0.31 0.0

SMStore6 1,875 31,875 66.7 2.70 1.3 0.4 0.0 562.5 0.0 0.31 0.0

SMStore7 1,875 31,875 66.7 2.70 1.3 0.4 0.0 562.5 0.0 0.31 0.0

SMStore8 1,875 31,875 66.7 2.70 1.3 0.4 0.0 562.5 0.0 0.45 0.0

Warehouse 52,045 1,385,797

Office 2,550 35,695 510.0 2.02 1.1 0.8 0.0 100.0 0.0 0.16 0.0

FineStorage 14,999 384,244 0.0 1.08 1.4 0.0 0.0 749.9 0.0 0.22 0.0

BulkStorage 34,497 965,859 0.0 0.31 0.9 0.2 0.0 80001.0 0.0 0.19 0.0
61

Table A-2 Reference Building Zone Internal Loads (SI units)

Building Type/Zone

Area

m2

Vol.

m3

m2/

person

1989

Lights

Wm2

2004

Lights

Wm2

Elec.

Proc.

W/m2

Gas 

Proc. 

W/m2

Vent. 

L/s

Exhst 

L/s

Infil. 

ACH 

SWH 

L/h

Quick Service Restaurant 232 708

Dining 116 354 1.39 15.45 22.60 129.1 0.0 833.6 0.0 0.64 0.0

Kitchen 116 354 18.58 16.64 12.91 301.3 1291.7 50.0 1557.4 0.64 151.4

Attic 232 262 1.00 0.0

Hospital 22,422 88,864

Basement 3,739 9,120 37.16 7.53 11.84 8.1 0.0 1006.2 0.0 0.00 0.0

ER_Exam1_Mult4_Flr_1 28 119 4.65 41.35 29.05 16.1 0.0 66.1 0.0 0.24 3.8

ER_Exam2_Flr_1 28 119 4.65 41.35 29.05 43.0 0.0 66.1 0.0 0.42 3.8

ER_Exam3_Mult4_Flr_1 28 119 4.65 41.35 29.05 16.1 0.0 66.1 0.0 0.18 3.8

ER_Exam4_Flr_1 28 119 4.65 41.35 29.05 43.0 0.0 66.1 0.0 0.42 3.8

ER_Exam5_Mult4_Flr_1 28 119 4.65 41.35 29.05 21.5 0.0 66.1 0.0 0.24 3.8

Office1_Mult4_Flr_1 14 60 13.27 25.78 11.84 11.8 0.0 10.5 0.0 0.24 0.0

Lobby_Flr_1 1,475 6,295 13.01 13.91 15.82 1.1 0.0 1133.9 0.0 0.07 0.0

Corridor_Flr_1 569 2,429 92.90 14.59 10.76 0.0 0.0 142.3 0.0 0.04 0.0

ER_NurseStat_Flr_1 1,236 5,274 14.86 22.63 12.05 14.6 0.0 2930.0 0.0 0.02 0.0

OR1_Flr_2 56 238 18.58 104.94 23.67 43.0 0.0 198.3 0.0 0.30 7.6

OR2_Mult5_Flr_2 56 238 18.58 104.94 23.67 43.0 0.0 198.3 0.0 0.12 7.6

OR3_Flr_2 56 238 18.58 104.94 23.67 43.0 0.0 198.3 0.0 0.18 7.6

OR4_Flr_2 223 952 18.58 84.88 23.67 43.0 0.0 793.1 0.0 0.00 22.7

IC_PatRoom1_Mult5_Flr_2 21 89 18.58 41.35 8.61 32.3 0.0 49.6 0.0 0.24 0.0

IC_PatRoom2_Flr_2 28 119 18.58 41.35 8.61 32.3 0.0 66.1 0.0 0.42 0.0

IC_PatRoom3_Mult6_Flr_2 21 89 18.58 41.35 8.61 32.3 0.0 49.6 0.0 0.24 0.0

ICU_Flr_2 618 2,638 4.65 41.35 8.61 32.3 0.0 1465.4 0.0 0.09 0.0

ICU_NurseSat_Flr_2 669 2,855 18.58 23.34 10.76 21.5 0.0 359.9 0.0 0.00 0.0

Corridor_Flr_2 569 2,429 92.90 14.59 10.76 0.0 0.0 142.3 0.0 0.04 0.0

OR_NurseSat_Flr_2 1,013 4,322 13.01 22.84 12.70 11.2 0.0 778.6 0.0 0.05 0.0

PatRoom1_Mult10_Flr_3 21 89 18.58 23.56 7.53 21.5 0.0 49.6 0.0 0.24 3.8

PatRoom2_Flr_3 35 149 18.58 23.56 7.53 21.5 0.0 82.6 0.0 0.38 3.8

PatRoom3_Mult10_Flr_3 20 86 18.58 23.56 7.53 21.5 0.0 47.9 0.0 0.24 3.8

PatRoom4_Flr_3 35 149 18.58 23.56 7.53 21.5 0.0 82.6 0.0 0.38 3.8

PatRoom5_Mult10_Flr_3 21 89 18.58 23.56 7.53 21.5 0.0 49.6 0.0 0.24 3.8

PhysTherapy_Flr_3 488 2,082 18.58 26.93 9.68 16.4 0.0 210.0 0.0 0.00 3.8

PatRoom6_Flr_3 28 119 18.58 23.56 7.53 21.5 0.0 66.1 0.0 0.42 3.8

PatRoom7_Mult10_Flr_3 20 86 18.58 23.56 7.53 21.5 0.0 47.9 0.0 0.24 3.8

PatRoom8_Flr_3 28 119 18.58 23.56 7.53 21.5 0.0 66.1 0.0 0.42 3.8

NurseSat_Lobby_Flr_3 906 3,866 13.01 22.96 12.70 11.2 0.0 696.4 0.0 0.00 0.0

Lab_Flr_3 265 1,130 18.58 22.65 15.06 43.0 0.0 142.5 0.0 0.00 7.6

Corridor_SE_Flr_3 567 2,419 92.90 14.60 10.76 0.0 0.0 141.7 0.0 0.02 0.0

Corridor_NW_Flr_3 567 2,419 92.90 14.60 10.76 0.0 0.0 141.7 0.0 0.02 0.0

PatRoom1_Mult10_Flr_4 21 89 18.58 23.56 7.53 21.5 0.0 49.6 0.0 0.24 3.8

PatRoom2_Flr_4 35 149 18.58 23.56 7.53 21.5 0.0 82.6 0.0 0.38 3.8

PatRoom3_Mult10_Flr_4 20 86 18.58 23.56 7.53 21.5 0.0 47.9 0.0 0.24 3.8

PatRoom4_Flr_4 35 149 18.58 23.56 7.53 21.5 0.0 82.6 0.0 0.38 3.8

PatRoom5_Mult10_Flr_4 21 89 18.58 23.56 7.53 21.5 0.0 49.6 0.0 0.24 3.8

Radiology_Flr_4 488 2,082 18.58 23.82 4.30 53.1 0.0 210.0 0.0 0.00 3.8

PatRoom6_Flr_4 28 119 18.58 23.56 7.53 21.5 0.0 66.1 0.0 0.42 3.8

PatRoom7_Mult10_Flr_4 20 86 18.58 23.56 7.53 21.5 0.0 47.9 0.0 0.24 3.8

PatRoom8_Flr_4 28 119 18.58 23.56 7.53 21.5 0.0 66.1 0.0 0.42 3.8

NurseSat_Lobby_Flr_4 906 3,866 13.01 22.96 12.70 11.2 0.0 696.4 0.0 0.00 0.0

Lab_Flr_4 265 1,130 18.58 22.65 15.06 43.0 0.0 142.5 0.0 0.00 7.6

Corridor_SE_Flr_4 567 2,419 92.90 14.60 10.76 0.0 0.0 141.7 0.0 0.02 0.0

Corridor_NW_Flr_4 567 2,419 92.90 14.60 10.76 0.0 0.0 141.7 0.0 0.02 0.0

Dining_Flr_5 697 2,974 9.29 27.72 9.68 10.8 0.0 750.0 0.0 0.34 0.0

NurseSat_Flr_5 1,041 4,441 13.01 22.81 12.70 11.2 0.0 800.0 0.0 0.28 0.0

Kitchen_Flr_5 929 3,965 18.58 15.29 12.91 80.7 304.8 400.0 2501.3 0.33 567.8

Office1_Flr_5 70 298 13.27 25.78 11.84 10.8 0.0 52.5 0.0 0.52 0.0

Office2_Mult5_Flr_5 70 297 13.27 25.78 11.84 10.8 0.0 52.5 0.0 0.37 0.0

Office3_Flr_5 70 297 13.27 25.78 11.84 10.8 0.0 52.5 0.0 0.52 0.0

Office4_Mult6_Flr_5 14 60 13.94 25.78 11.84 10.8 0.0 10.0 0.0 0.49 0.0
62

Building Type/Zone

Area

m2

Vol.

m3

m2/

person

1989

Lights

Wm2

2004

Lights

Wm2

Elec.

Proc.

W/m2

Gas 

Proc. 

W/m2

Vent. 

L/s

Exhst 

L/s

Infil. 

ACH 

SWH 

L/h

Corridor_Flr_5 502 2,141 92.90 14.60 10.76 0.0 0.0 125.4 0.0 0.29 0.0

Large Hotel 11,345 35,185

Basement 1,979 4,826 37.16 7.53 10.76 5.4 0.0 502.6 0.0 0.00 0.0

Retail_1_Flr_1 67 266 6.19 38.09 16.14 10.8 0.0 102.2 0.0 0.56 0.0

Retail_2_Flr_1 78 308 6.19 38.09 16.14 10.8 0.0 118.4 0.0 0.09 0.0

Mech_Flr_1 164 651 0.00 8.60 16.14 5.4 0.0 41.7 0.0 0.11 0.0

Storage_Flr_1 95 375 46.45 3.96 9.68 2.7 0.0 72.2 0.0 0.11 0.0

Laundry_Flr_1 78 309 23.23 12.23 6.46 61.7 535.9 23.8 236.0 0.30 592.8

Cafe_Flr_1 189 748 1.39 15.74 13.99 5.4 0.0 1279.1 0.0 0.50 0.0

Lobby_Flr_1 1,308 5,184 3.10 20.28 11.84 8.1 0.0 3987.4 0.0 0.10 0.0

Room_1_Flr_3 39 119 26.01 19.09 11.84 6.8 0.0 14.2 0.0 0.37 4.7

Room_2_Flr_3 39 119 26.01 19.09 11.84 6.8 0.0 14.2 0.0 0.37 4.7

Room_3_Mult19_Flr_3 25 75 16.35 19.09 11.84 10.5 0.0 14.2 0.0 0.16 89.9

Room_4_Mult19_Flr_3 25 75 16.35 19.09 11.84 10.5 0.0 14.2 0.0 0.16 89.9

Room_5_Flr_3 39 119 26.01 19.09 11.84 6.8 0.0 14.2 0.0 0.37 4.7

Room_6_Flr_3 39 119 26.01 19.09 11.84 6.8 0.0 14.2 0.0 0.37 4.7

Corridor_Flr_3 389 1,187 92.90 13.11 5.38 0.0 0.0 98.9 0.0 0.04 0.0

Room_1_Flr_6 39 119 26.01 19.09 11.84 6.8 0.0 14.2 0.0 0.72 4.7

Room_2_Flr_6 39 119 26.01 19.09 11.84 6.8 0.0 14.2 0.0 0.72 4.7

Room_3_Mult9_Flr_6 25 75 16.35 19.09 11.84 10.5 0.0 14.2 0.0 1.28 42.6

Banquet_Flr_6 332 1,011 1.39 27.55 13.99 67.8 0.0 2246.2 0.0 0.46 0.0

Dining_Flr_6 332 1,011 1.39 27.55 13.99 67.8 0.0 2246.2 0.0 0.46 0.0

Kitchen_Flr_6 103 315 18.58 16.83 12.91 508.0 1612.8 39.4 1887.8 0.66 503.5

Corridor_Flr_6 412 1,256 92.90 13.08 5.38 0.0 0.0 104.7 0.0 0.48 0.0

Large Office 46,320 178,146

Basement 3,563 8,690 37.16 7.53 10.76 10.76 0.0 958.8 0.0 0.15 0.0

Perimeter_bot_ZN_3 313 860 18.58 16.14 10.76 10.76 0.0 168.7 0.0 0.30 0.0

Perimeter_bot_ZN_2 202 554 18.58 16.14 10.76 10.76 0.0 108.7 0.0 0.30 0.0

Perimeter_bot_ZN_1 313 860 18.58 16.14 10.76 10.76 0.0 168.7 0.0 0.30 0.0

Perimeter_bot_ZN_4 202 554 18.58 16.14 10.76 10.76 0.0 108.7 0.0 0.30 0.0

Core_bottom 2,532 6,949 18.58 16.14 10.76 10.76 0.0 1362.9 0.0 0.15 80.6

Perimeter_mid_ZN_3 313 860 18.58 16.14 10.76 10.76 0.0 168.7 0.0 0.30 0.0

Perimeter_mid_ZN_2 202 554 18.58 16.14 10.76 10.76 0.0 108.7 0.0 0.30 0.0

Perimeter_mid_ZN_1 313 860 18.58 16.14 10.76 10.76 0.0 168.7 0.0 0.30 0.0

Perimeter_mid_ZN_4 202 554 18.58 16.14 10.76 10.76 0.0 108.7 0.0 0.30 0.0

Core_mid 2,532 6,949 18.58 16.14 10.76 10.76 0.0 1362.9 0.0 0.15 80.6

Perimeter_top_ZN_3 313 860 18.58 16.14 10.76 10.76 0.0 168.7 0.0 0.30 0.0

Perimeter_top_ZN_2 202 554 18.58 16.14 10.76 10.76 0.0 108.7 0.0 0.30 0.0

Perimeter_top_ZN_1 313 860 18.58 16.14 10.76 10.76 0.0 168.7 0.0 0.30 0.0

Perimeter_top_ZN_4 202 554 18.58 16.14 10.76 10.76 0.0 108.7 0.0 0.30 0.0

Core_top 2,532 6,949 18.58 16.14 10.76 10.76 0.0 1362.9 0.0 0.15 80.6

Groundfloor_plenum 3,563 4,344 0.00 0.0

Midfloor_plenum 3,563 4,344 0.00 0.0

Topfloor_plenum 3,563 4,344 0.00 0.0

Medium Office 4,982 19,741

Perimeter_bot_ZN_3 207 569 18.58 16.89 10.76 10.76 0.0 111.6 0.0 0.26 0.0

Perimeter_bot_ZN_2 131 360 18.58 16.89 10.76 10.76 0.0 70.6 0.0 0.28 0.0

Perimeter_bot_ZN_1 207 569 18.58 16.89 10.76 10.76 0.0 111.6 0.0 0.26 0.0

Perimeter_bot_ZN_4 131 360 18.58 16.89 10.76 10.76 0.0 70.6 0.0 0.28 0.0

Core_bottom 984 2,698 18.58 16.89 10.76 10.76 0.0 529.3 0.0 0.00 37.5

Perimeter_mid_ZN_3 207 569 18.58 16.89 10.76 10.76 0.0 111.6 0.0 0.26 0.0

Perimeter_mid_ZN_2 131 360 18.58 16.89 10.76 10.76 0.0 70.6 0.0 0.28 0.0

Perimeter_mid_ZN_1 207 569 18.58 16.89 10.76 10.76 0.0 111.6 0.0 0.26 0.0

Perimeter_mid_ZN_4 131 360 18.58 16.89 10.76 10.76 0.0 70.6 0.0 0.28 0.0

Core_mid 984 2,698 18.58 16.89 10.76 10.76 0.0 529.3 0.0 0.00 37.5

Perimeter_top_ZN_3 207 569 18.58 16.89 10.76 10.76 0.0 111.6 0.0 0.66 0.0

Perimeter_top_ZN_2 131 360 18.58 16.89 10.76 10.76 0.0 70.6 0.0 0.67 0.0
63

Building Type/Zone

Area

m2

Vol.

m3

m2/

person

1989

Lights

Wm2

2004

Lights

Wm2

Elec.

Proc.

W/m2

Gas 

Proc. 

W/m2

Vent. 

L/s

Exhst 

L/s

Infil. 

ACH 

SWH 

L/h

Perimeter_top_ZN_1 207 569 18.58 16.89 10.76 10.76 0.0 111.6 0.0 0.66 0.0

Perimeter_top_ZN_4 131 360 18.58 16.89 10.76 10.76 0.0 70.6 0.0 0.67 0.0

Core_top 984 2,698 18.58 16.89 10.76 10.76 0.0 529.3 0.0 0.40 37.5

Firstfloor_plenum 1,661 2,025 0.11 0.0

Midfloor_plenum 1,661 2,025 0.11 0.0

Topfloor_plenum 1,661 2,025 1.00 0.0

Midrise Apartment 3,135 9,553

G SW APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.24 13.2

G NW APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.24 13.2

OFFICE 88 269 44.12 21.99 10.76 12.9 0.0 18.9 0.0 0.24 0.0

G NE APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.24 13.2

G N1 APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.14 13.2

G N2 APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.14 13.2

G S1 APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.14 13.2

G S2 APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.14 13.2

M SW APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.24 13.2

M NW APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.24 13.2

M SE APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.24 13.2

M NE APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.24 13.2

M N1 APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.14 13.2

M N2 APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.14 13.2

M S1 APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.14 13.2

M S2 APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.14 13.2

T SW APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.59 13.2

T NW APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.59 13.2

T SE APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.59 13.2

T NE APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.59 13.2

T N1 APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.50 13.2

T N2 APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.50 13.2

T S1 APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.50 13.2

T S2 APARTMENT 88 269 35.30 3.87 3.88 5.4 0.0 42.5 0.0 0.50 13.2

T CORRIDOR 78 237 0.00 9.91 5.38 0.0 0.0 19.7 0.0 0.40 0.0

G CORRIDOR 78 237 0.00 9.91 5.38 0.0 0.0 19.7 0.0 0.05 0.0

M CORRIDOR 78 237 0.00 9.91 5.38 0.0 0.0 19.7 0.0 0.05 0.0

Outpatient Health Care 3,804 11,932

Floor 1 Anesthesia 10 31 0.00 32.29 21.5 0.0 61.2 68.0 0.30 3.8

Floor 1 Bio Haz 5 16 0.00 9.69 1.1 0.0 4.0 0.0 0.00 0.0

Floor 1 Café 39 119 1.00 9.69 10.8 0.0 368.3 0.0 0.17 0.0

Floor 1 Clean 12 36 5.00 12.92 21.5 0.0 17.8 0.0 0.00 0.0

Floor 1 Clean Work 15 47 5.00 12.92 21.5 0.0 23.4 0.0 0.00 0.0

Floor 1 Dictation 12 36 20.00 11.84 11.8 0.0 5.5 0.0 0.00 0.0

Floor 1 Dressing Room 4 13 20.00 11.84 11.8 0.0 2.0 0.0 0.71 0.0

Floor 1 Electrical Room 9 28 0.00 16.15 53.8 0.0 2.3 0.0 0.25 0.0

Floor 1 Elevator Pump Room 8 26 0.00 16.15 53.8 0.0 2.1 0.0 0.78 0.0

Floor 1 Humid 5 15 20.00 11.84 11.8 0.0 2.4 0.0 0.00 0.0

Floor 1 IT Hall 13 40 0.00 10.76 4.3 0.0 3.3 0.0 0.00 0.0

Floor 1 IT Room 10 32 20.00 11.84 11.8 0.0 4.9 0.0 0.00 0.0

Floor 1 Lobby 58 176 3.33 13.99 11.8 0.0 122.7 0.0 0.13 0.0

Floor 1 Lobby Hall 22 68 0.00 10.76 4.3 0.0 5.7 0.0 0.00 0.0

Floor 1 Lobby Toilet 5 15 0.00 9.69 4.3 0.0 51.0 42.5 0.40 0.0

Floor 1 Locker Room 61 187 6.67 8.61 32.3 0.0 65.1 0.0 0.12 0.0

Floor 1 Locker Room Hall 46 140 0.00 10.76 4.3 0.0 11.7 0.0 0.00 0.0

Floor 1 Lounge 33 102 6.67 8.61 32.3 0.0 35.5 0.0 0.00 0.0

Floor 1 Med Gas 5 16 0.00 9.69 1.1 0.0 4.0 0.0 0.96 0.0

Floor 1 MRI Control Room 16 48 5.00 4.31 107.6 0.0 23.8 79.3 0.11 3.8

Floor 1 MRI Hall 14 42 0.00 10.76 4.3 0.0 3.5 0.0 0.00 0.0
64

Building Type/Zone

Area

m2

Vol.

m3

m2/

person

1989

Lights

Wm2

2004

Lights

Wm2

Elec.

Proc.

W/m2

Gas 

Proc. 

W/m2

Vent. 

L/s

Exhst 

L/s

Infil. 

ACH 

SWH 

L/h

Floor 1 MRI Room 41 125 5.00 4.31 107.6 0.0 62.3 207.7 0.00 3.8

Floor 1 MRI Toilet 5 15 0.00 9.69 4.3 0.0 51.0 42.5 0.40 0.0

Floor 1 Nourishment 17 52 5.00 10.76 21.5 0.0 31.9 0.0 0.00 0.0

Floor 1 Nurse Hall 46 140 0.00 10.76 4.3 0.0 11.7 0.0 0.00 0.0

Floor 1 Nurse Janitor 5 15 0.00 9.69 1.1 0.0 3.8 0.0 0.00 0.0

Floor 1 Nurse Station 24 74 5.00 10.76 21.5 0.0 45.8 0.0 0.00 0.0

Floor 1 Nurse Toilet 5 15 0.00 9.69 4.3 0.0 51.0 42.5 0.00 0.0

Floor 1 Office 45 137 20.00 11.84 11.8 0.0 21.2 0.0 0.00 0.0

Floor 1 Operating Room 1 43 130 5.00 23.68 43.1 75.3 108.5 0.0 0.33 22.7

Floor 1 Operating Room 2 45 136 5.00 23.68 43.1 75.3 113.3 0.0 0.18 22.7

Floor 1 Operating Room 3 44 135 5.00 23.68 43.1 75.3 112.3 0.0 0.00 22.7

Floor 1 PACU 10 31 5.00 8.61 32.3 0.0 17.0 0.0 0.00 3.8

Floor 1 Pre-Op Hall 49 150 0.00 10.76 4.3 0.0 12.5 0.0 0.00 0.0

Floor 1 Pre-Op Room 1 18 54 10.00 7.53 21.5 0.0 29.7 0.0 0.08 3.8

Floor 1 Pre-Op Room 2 31 96 10.00 7.53 21.5 0.0 53.2 0.0 0.00 3.8

Floor 1 Pre-Op Toilet 5 15 0.00 9.69 4.3 0.0 51.0 42.5 0.40 0.0

Floor 1 Procedure Room 26 81 5.00 29.06 32.3 0.0 67.2 0.0 0.24 3.8

Floor 1 Reception 47 144 3.33 13.99 11.8 0.0 100.4 0.0 0.09 0.0

Floor 1 Reception Hall 12 36 0.00 10.76 4.3 0.0 3.0 0.0 0.00 0.0

Floor 1 Recovery Room 50 153 5.00 8.61 32.3 0.0 84.9 0.0 0.30 3.8

Floor 1 Scheduling 11 34 20.00 11.84 11.8 0.0 5.2 0.0 0.21 0.0

Floor 1 Scrub 8 24 0.00 10.76 4.3 0.0 2.0 0.0 0.00 0.0

Floor 1 Soil 12 36 5.00 12.92 21.5 0.0 89.2 99.1 0.00 0.0

Floor 1 Soil Hold 5 16 5.00 12.92 21.5 0.0 39.6 44.0 0.00 0.0

Floor 1 Soil Work 17 51 5.00 12.92 21.5 0.0 127.4 141.6 0.00 0.0

Floor 1 Step Down 28 85 5.00 8.61 32.3 0.0 47.2 0.0 0.44 3.8

Floor 1 Sterile Hall 57 174 0.00 10.76 4.3 0.0 14.5 0.0 0.05 0.0

Floor 1 Sterile Storage 37 112 0.00 9.69 1.1 0.0 28.0 0.0 0.00 0.0

Floor 1 Storage 85 261 0.00 9.69 1.1 0.0 65.1 0.0 0.24 0.0

Floor 1 Sub-Sterile 18 56 0.00 10.76 4.3 0.0 4.6 0.0 0.26 0.0

Floor 1 Utility Hall 24 72 0.00 10.76 4.3 0.0 6.0 0.0 0.22 0.0

Floor 1 Utility Janitor 4 12 0.00 9.69 1.1 0.0 3.0 0.0 0.00 0.0

Floor 1 Utility Room 33 102 0.00 9.69 1.1 0.0 25.5 0.0 0.18 0.0

Floor 1 Vestibule 7 20 0.00 10.76 4.3 0.0 1.7 0.0 0.40 0.0

Floor 2 Conference 31 95 2.00 13.99 10.8 0.0 147.3 0.0 0.43 0.0

Floor 2 Conference Toilet 6 18 0.00 9.69 4.3 0.0 60.4 50.3 0.00 0.0

Floor 2 Dictation 7 20 20.00 11.84 11.8 0.0 3.1 0.0 0.00 0.0

Floor 2 Exam 1 33 102 5.00 16.15 11.8 0.0 51.0 0.0 0.42 0.0

Floor 2 Exam 2 50 153 5.00 16.15 11.8 0.0 76.4 0.0 0.12 0.0

Floor 2 Exam 3 67 204 5.00 16.15 11.8 0.0 101.9 0.0 0.12 0.0

Floor 2 Exam 4 8 24 5.00 16.15 11.8 0.0 11.9 0.0 0.30 0.0

Floor 2 Exam 5 33 99 5.00 16.15 11.8 0.0 49.5 0.0 0.26 0.0

Floor 2 Exam 6 21 64 5.00 16.15 11.8 0.0 31.9 0.0 0.24 0.0

Floor 2 Exam 7 74 224 5.00 16.15 11.8 0.0 112.1 0.0 0.11 0.0

Floor 2 Exam 8 25 76 5.00 16.15 11.8 0.0 38.2 0.0 0.24 0.0

Floor 2 Exam 9 37 112 5.00 16.15 11.8 0.0 56.1 0.0 0.11 0.0

Floor 2 Exam Hall 1 17 51 0.00 10.76 4.3 0.0 4.2 0.0 0.12 0.0

Floor 2 Exam Hall 2 17 51 0.00 10.76 4.3 0.0 4.2 0.0 0.12 0.0

Floor 2 Exam Hall 3 17 51 0.00 10.76 4.3 0.0 4.2 0.0 0.12 0.0

Floor 2 Exam Hall 4 18 56 0.00 10.76 4.3 0.0 4.7 0.0 0.11 0.0

Floor 2 Exam Hall 5 18 56 0.00 10.76 4.3 0.0 4.7 0.0 0.11 0.0

Floor 2 Exam Hall 6 18 56 0.00 10.76 4.3 0.0 4.7 0.0 0.11 0.0

Floor 2 Janitor 6 18 0.00 9.69 1.1 0.0 4.5 0.0 0.91 0.0

Floor 2 Lounge 7 23 6.67 8.61 32.3 0.0 7.9 0.0 0.00 0.0

Floor 2 Nurse Station 1 14 42 5.00 10.76 21.5 0.0 26.3 0.0 0.00 0.0

Floor 2 Nurse Station 2 17 51 5.00 10.76 21.5 0.0 31.6 0.0 0.00 0.0
65

Building Type/Zone

Area

m2

Vol.

m3

m2/

person

1989

Lights

Wm2

2004

Lights

Wm2

Elec.

Proc.

W/m2

Gas 

Proc. 

W/m2

Vent. 

L/s

Exhst 

L/s

Infil. 

ACH 

SWH 

L/h

Floor 2 Office 52 159 20.00 11.84 11.8 0.0 24.6 0.0 0.26 0.0

Floor 2 Office Hall 41 126 0.00 10.76 4.3 0.0 10.5 0.0 0.00 0.0

Floor 2 Reception 91 279 3.33 13.99 11.8 0.0 194.1 0.0 0.18 0.0

Floor 2 Reception Hall 52 160 0.00 10.76 4.3 0.0 13.3 0.0 0.60 0.0

Floor 2 Reception Toilet 12 36 0.00 9.69 4.3 0.0 118.9 99.1 0.00 0.0

Floor 2 Scheduling 1 30 92 20.00 11.84 11.8 0.0 14.2 0.0 0.00 0.0

Floor 2 Scheduling 2 32 97 20.00 11.84 11.8 0.0 15.0 0.0 0.00 0.0

Floor 2 Storage 1 5 16 0.00 9.69 1.1 0.0 4.0 0.0 0.00 0.0

Floor 2 Storage 2 11 34 0.00 9.69 1.1 0.0 8.5 0.0 0.00 0.0

Floor 2 Storage 3 13 41 0.00 9.69 1.1 0.0 10.2 0.0 0.00 0.0

Floor 2 Utility 12 36 0.00 9.69 1.1 0.0 8.9 0.0 0.26 0.0

Floor 2 Work 157 479 20.00 11.84 11.8 0.0 74.1 0.0 0.05 0.0

Floor 2 Work Hall 77 236 0.00 10.76 4.3 0.0 19.7 0.0 0.03 0.0

Floor 2 Work Toilet 5 15 0.00 9.69 4.3 0.0 51.0 42.5 0.40 0.0

Floor 2 X-Ray 84 255 5.00 4.31 107.6 0.0 127.4 0.0 0.00 3.8

Floor 3 Dressing Room 4 12 20.00 11.84 11.8 0.0 1.8 0.0 0.00 0.0

Floor 3 Elevator Hall 34 105 0.00 10.76 4.3 0.0 8.7 0.0 0.04 0.0

Floor 3 Humid 10 31 20.00 11.84 11.8 0.0 4.7 0.0 0.00 0.0

Floor 3 Janitor 6 18 0.00 9.69 1.1 0.0 4.5 0.0 0.91 0.0

Floor 3 Locker 11 34 6.67 8.61 32.3 0.0 11.8 0.0 0.00 0.0

Floor 3 Lounge 71 215 6.67 8.61 32.3 0.0 74.9 0.0 0.11 0.0

Floor 3 Lounge Toilet 18 54 0.00 9.69 4.3 0.0 181.2 151.0 0.22 0.0

Floor 3 Mechanical 33 99 0.00 16.15 53.8 0.0 8.3 0.0 0.26 0.0

Floor 3 Mechanical Hall 28 85 0.00 10.76 4.3 0.0 7.1 0.0 0.00 0.0

Floor 3 Office 282 860 20.00 11.84 11.8 0.0 133.1 0.0 0.09 0.0

Floor 3 Office Hall 77 236 0.00 10.76 4.3 0.0 19.7 0.0 0.03 0.0

Floor 3 Office Toilet 5 15 0.00 9.69 4.3 0.0 51.0 42.5 0.40 0.0

Floor 3 Physical Therapy 1 121 368 5.00 9.69 16.2 0.0 171.0 0.0 0.23 3.8

Floor 3 Physical Therapy 2 55 168 5.00 9.69 16.2 0.0 77.9 0.0 0.00 3.8

Floor 3 Physical Therapy Toilet 8 24 0.00 9.69 4.3 0.0 79.3 66.1 0.00 0.0

Floor 3 Storage 1 10 31 0.00 9.69 1.1 0.0 7.6 0.0 0.00 0.0

Floor 3 Storage 2 8 24 0.00 9.69 1.1 0.0 5.9 0.0 0.00 0.0

Floor 3 Treatment 44 135 5.00 16.15 11.8 0.0 67.4 0.0 0.00 0.0

Floor 3 Undeveloped 1 211 642 20.00 11.84 11.8 0.0 160.5 0.0 0.11 0.0

Floor 3 Undeveloped 2 107 326 20.00 11.84 11.8 0.0 81.5 0.0 0.17 0.0

Floor 3 Utility 20 61 0.00 9.69 1.1 0.0 15.3 0.0 0.00 0.0

Floor 3 Work 53 163 20.00 11.84 11.8 0.0 25.2 0.0 0.26 0.0

NE Stair 16 143 0.00 10.76 4.3 0.0 4.0 0.0 0.74 0.0

NW Elevator 13 119 0.00 10.76 4.3 0.0 3.3 0.0 0.69 0.0

NW Stair 18 163 0.00 10.76 4.3 0.0 4.5 0.0 0.74 0.0

SW Stair 9 82 0.00 10.76 4.3 0.0 2.3 0.0 0.74 0.0

Retail 2,294 13,993

Back_Space 380 2,317 27.87 12.55 8.61 8.1 0.0 284.9 0.0 0.37 0.0

Core_Retail 1,600 9,763 6.19 36.25 18.29 3.2 0.0 2400.7 0.0 0.22 0.0

Point_of_Sale 151 920 6.19 36.25 18.29 21.5 0.0 226.2 0.0 0.40 0.0

Front_Retail 151 920 6.19 36.25 18.29 3.2 0.0 226.2 0.0 0.40 0.0

Front_Entry 12 73 6.19 36.25 11.84 0.0 0.0 0.0 0.0 0.54 0.0

Primary Education 6,871 27,484

CORNER_CLASS_1_POD_1_ZN

_1_FLR_1 99 396 4.00 21.52 15.06 15.0 0.0 198.0 0.0 0.49 0.0

MULT_CLASS_1_POD_1_ZN_1_

FLR_1 477 1,908 4.00 21.52 15.06 15.0 0.0 954.0 0.0 0.39 0.0

CORRIDOR_POD_1_ZN_1_FLR_

1 192 768 10.00 21.52 5.38 4.0 0.0 96.0 0.0 0.29 0.0

CORNER_CLASS_2_POD_1_ZN

_1_FLR_1 99 396 4.00 21.52 15.06 15.0 0.0 198.0 0.0 0.49 0.0
66

Building Type/Zone

Area

m2

Vol.

m3

m2/

person

1989

Lights

Wm2

2004

Lights

Wm2

Elec.

Proc.

W/m2

Gas 

Proc. 

W/m2

Vent. 

L/s

Exhst 

L/s

Infil. 

ACH 

SWH 

L/h

MULT_CLASS_2_POD_1_ZN_1_

FLR_1 477 1,908 4.00 21.52 15.06 15.0 0.0 954.0 0.0 0.39 0.0

CORNER_CLASS_1_POD_2_ZN

_1_FLR_1 99 396 4.00 21.52 15.06 15.0 0.0 198.0 0.0 0.49 0.0

MULT_CLASS_1_POD_2_ZN_1_

FLR_1 477 1,908 4.00 21.52 15.06 15.0 0.0 954.0 0.0 0.39 0.0

CORRIDOR_POD_2_ZN_1_FLR_

1 192 768 10.00 9.69 5.38 4.0 0.0 96.0 0.0 0.29 0.0

CORNER_CLASS_2_POD_2_ZN

_1_FLR_1 99 396 4.00 21.52 15.06 15.0 0.0 198.0 0.0 0.49 0.0

MULT_CLASS_2_POD_2_ZN_1_

FLR_1 477 1,908 4.00 21.52 15.06 15.0 0.0 954.0 0.0 0.39 0.0

CORNER_CLASS_1_POD_3_ZN

_1_FLR_1 99 396 4.00 21.52 15.06 15.0 0.0 198.0 0.0 0.49 0.0

MULT_CLASS_1_POD_3_ZN_1_

FLR_1 477 1,908 4.00 21.52 15.06 15.0 0.0 954.0 0.0 0.39 0.0

CORRIDOR_POD_3_ZN_1_FLR_

1 192 768 10.00 9.69 5.38 4.0 0.0 96.0 0.0 0.29 0.0

CORNER_CLASS_2_POD_3_ZN

_1_FLR_1 99 396 4.00 21.52 15.06 15.0 0.0 198.0 0.0 0.49 0.0

MULT_CLASS_2_POD_3_ZN_1_

FLR_1 315 1,260 4.00 21.52 15.06 8.1 0.0 630.0 0.0 0.39 0.0

COMPUTER_CLASS_ZN_1_FLR

_1 162 648 3.33 21.52 15.06 20.0 0.0 389.2 0.0 0.39 0.0

MAIN_CORRIDOR_ZN_1_FLR_1 546 2,184 0.00 11.14 5.38 4.0 0.0 273.0 0.0 0.29 0.0

LOBBY_ZN_1_FLR_1 171 684 0.00 12.26 13.99 4.0 0.0 85.5 0.0 0.39 0.0

MECH_ZN_1_FLR_1 252 1,008 100.00 8.26 16.14 10.0 0.0 63.0 0.0 0.27 0.0

BATH_ZN_1_FLR_1 190 760 100.00 9.70 9.68 4.0 0.0 300.0 283.2 0.33 4.00

OFFICES_ZN_1_FLR_1 441 1,764 20.00 20.33 11.84 10.8 0.0 220.5 0.0 0.38 0.0

GYM_ZN_1_FLR_1 357 1,428 3.33 11.47 15.06 5.0 0.0 1072.1 0.0 0.32 0.0

KITCHEN_ZN_1_FLR_1 168 672 6.67 17.20 12.91 190.5 954.1 201.5 1557.4 0.32 4.00

CAFETERIA_ZN_1_FLR_1 315 1,260 1.39 15.05 15.06 25.4 0.0 2260.4 0.0 0.40 0.0

LIBRARY_MEDIA_CENTER_ZN_

1_FLR_1 399 1,596 4.35 22.75 13.99 15.0 0.0 733.8 0.0 0.38 0.0

Secondary Education 19,592 95,216

CORNER_CLASS_1_POD_1_ZN

_1_FLR_1 99 396 4.00 21.52 15.06 10.0 0.0 198.0 0.0 0.22 0.0

CORNER_CLASS_1_POD_1_ZN

_1_FLR_2 99 396 4.00 21.52 15.06 10.0 0.0 198.0 0.0 0.49 0.0

MULT_CLASS_1_POD_1_ZN_1_

FLR_1 477 1,908 4.00 21.52 15.06 10.0 0.0 954.0 0.0 0.12 0.0

MULT_CLASS_1_POD_1_ZN_1_

FLR_2 477 1,908 4.00 21.52 15.06 10.0 0.0 954.0 0.0 0.39 0.0

CORRIDOR_POD_1_ZN_1_FLR

_1 320 1,280 10.00 9.25 5.38 4.0 0.0 160.0 0.0 0.02 0.0

CORRIDOR_POD_1_ZN_1_FLR

_2 320 1,280 10.00 9.25 5.38 4.0 0.0 160.0 0.0 0.29 0.0

CORNER_CLASS_2_POD_1_ZN

_1_FLR_1 99 396 4.00 21.52 15.06 10.0 0.0 198.0 0.0 0.22 0.0

CORNER_CLASS_2_POD_1_ZN

_1_FLR_2 99 396 4.00 21.52 15.06 10.0 0.0 198.0 0.0 0.49 0.0

MULT_CLASS_2_POD_1_ZN_1_

FLR_1 477 1,908 4.00 21.52 15.06 10.0 0.0 954.0 0.0 0.12 0.0

MULT_CLASS_2_POD_1_ZN_1_

FLR_2 477 1,908 4.00 21.52 15.06 10.0 0.0 954.0 0.0 0.39 0.0

CORNER_CLASS_1_POD_2_ZN

_1_FLR_1 99 396 4.00 21.52 15.06 10.0 0.0 198.0 0.0 0.22 0.0

CORNER_CLASS_1_POD_2_ZN

_1_FLR_2 99 396 4.00 21.52 15.06 10.0 0.0 198.0 0.0 0.49 0.0

MULT_CLASS_1_POD_2_ZN_1_ 477 1,908 4.00 21.52 15.06 10.0 0.0 954.0 0.0 0.12 0.0
67

Building Type/Zone

Area

m2

Vol.

m3

m2/

person

1989

Lights

Wm2

2004

Lights

Wm2

Elec.

Proc.

W/m2

Gas 

Proc. 

W/m2

Vent. 

L/s

Exhst 

L/s

Infil. 

ACH 

SWH 

L/h

FLR_1 

MULT_CLASS_1_POD_2_ZN_1_

FLR_2 477 1,908 4.00 21.52 15.06 10.0 0.0 954.0 0.0 0.39 0.0

CORRIDOR_POD_2_ZN_1_FLR

_1 320 1,280 10.00 9.25 5.38 4.0 0.0 160.0 0.0 0.02 0.0

CORRIDOR_POD_2_ZN_1_FLR

_2 320 1,280 10.00 9.25 5.38 4.0 0.0 160.0 0.0 0.29 0.0

CORNER_CLASS_2_POD_2_ZN

_1_FLR_1 99 396 4.00 21.52 15.06 10.0 0.0 198.0 0.0 0.22 0.0

CORNER_CLASS_2_POD_2_ZN

_1_FLR_2 99 396 4.00 21.52 15.06 10.0 0.0 198.0 0.0 0.49 0.0

MULT_CLASS_2_POD_2_ZN_1_

FLR_1 477 1,908 4.00 21.52 15.06 10.0 0.0 954.0 0.0 0.12 0.0

MULT_CLASS_2_POD_2_ZN_1_

FLR_2 477 1,908 4.00 21.52 15.06 10.0 0.0 954.0 0.0 0.39 0.0

CORNER_CLASS_1_POD_3_ZN

_1_FLR_1 99 396 4.00 21.52 15.06 10.0 0.0 198.0 0.0 0.22 0.0

CORNER_CLASS_1_POD_3_ZN

_1_FLR_2 99 396 4.00 21.52 15.06 10.0 0.0 198.0 0.0 0.49 0.0

MULT_CLASS_1_POD_3_ZN_1_

FLR_1 477 1,908 4.00 21.52 15.06 10.0 0.0 954.0 0.0 0.12 0.0

MULT_CLASS_1_POD_3_ZN_1_

FLR_2 477 1,908 4.00 21.52 15.06 20.0 0.0 954.0 0.0 0.39 0.0

CORRIDOR_POD_3_ZN_1_FLR

_1 320 1,280 10.00 9.25 5.38 4.0 0.0 160.0 0.0 0.02 0.0

CORRIDOR_POD_3_ZN_1_FLR

_2 320 1,280 10.00 9.25 5.38 4.0 0.0 160.0 0.0 0.29 0.0

CORNER_CLASS_2_POD_3_ZN

_1_FLR_1 99 396 4.00 21.52 15.06 10.0 0.0 198.0 0.0 0.22 0.0

CORNER_CLASS_2_POD_3_ZN

_1_FLR_2 99 396 4.00 21.52 15.06 10.0 0.0 198.0 0.0 0.49 0.0

MULT_CLASS_2_POD_3_ZN_1_

FLR_1 477 1,908 4.00 21.52 15.06 10.0 0.0 954.0 0.0 0.12 0.0

MULT_CLASS_2_POD_3_ZN_1_

FLR_2 477 1,908 4.00 21.52 15.06 20.0 0.0 954.0 0.0 0.39 0.0

MAIN_CORRIDOR_ZN_1_FLR_1 1,140 4,560 0.00 10.74 5.38 4.0 0.0 570.0 0.0 0.05 0.0

MAIN_CORRIDOR_ZN_1_FLR_2 1,140 4,560 0.00 10.74 5.38 4.0 0.0 570.0 0.0 0.32 0.0

LOBBY_ZN_1_FLR_1 210 840 0.00 12.00 13.99 4.0 0.0 105.0 0.0 0.08 0.0

LOBBY_ZN_1_FLR_2 210 840 0.00 12.00 13.99 4.0 0.0 105.0 0.0 0.35 0.0

BATHROOMS_ZN_1_FLR_1 210 840 10.00 9.60 9.68 4.0 0.0 300.0 0.0 0.15 4.00

BATHROOMS_ZN_1_FLR_2 210 840 10.00 9.60 9.68 4.0 0.0 300.0 0.0 0.42 4.00

OFFICES_ZN_1_FLR_1 532 2,128 20.00 20.09 11.84 10.8 0.0 266.0 0.0 0.11 0.0

OFFICES_ZN_1_FLR_2 532 2,128 20.00 20.09 11.84 10.8 0.0 266.0 0.0 0.38 0.0

GYM_ZN_1_FLR_1 1,976 15,808 1.00 11.38 15.06 5.0 0.0 19760.0 0.0 0.14 717.2

AUX_GYM_ZN_1_FLR_1 1,248 9,984 3.33 11.81 15.06 5.0 0.0 3747.7 0.0 0.20 0.0

AUDITORIUM_ZN_1_FLR_1 988 7,904 1.00 12.08 9.68 5.0 0.0 7904.0 0.0 0.21 0.0

KITCHEN_ZN_1_FLR_1 216 864 6.67 16.76 12.91 222.2 1119.0 259.1 1887.8 0.05 4.00

LIBRARY_MEDIA_CENTER_ZN_

1_FLR_2 840 3,360 4.35 0.00 13.99 10.0 0.0 1544.8 0.0 0.35 0.0

CAFETERIA_ZN_1_FLR_1 624 2,496 1.39 14.38 15.06 19.3 0.0 4477.8 0.0 0.09 0.0

MECH_ZN_1_FLR_1 342 1,368 100.00 8.05 16.14 4.0 0.0 85.5 0.0 0.00 0.0

MECH_ZN_1_FLR_2 342 1,368 100.00 8.05 16.14 4.0 0.0 85.5 0.0 0.00 0.0

Full Service Restaurant 511 1,558

Dining 372 1,133 1.39 27.38 22.60 60.3 0.0 2667.7 0.0 0.52 0.0

Kitchen 139 425 18.58 16.37 12.91 376.6 1197.9 60.0 1887.8 0.63 503.5

Attic 511 856 1.00

Supermarket 4,181 25,493

Office 89 542 18.58 21.36 11.84 8.1 0.0 47.8 0.0 0.41 0.0
68

Building Type/Zone

Area

m2

Vol.

m3

m2/

person

1989

Lights

Wm2

2004

Lights

Wm2

Elec.

Proc.

W/m2

Gas 

Proc. 

W/m2

Vent. 

L/s

Exhst 

L/s

Infil. 

ACH 

SWH 

L/h

Dry Storage 622 3,792 27.87 11.90 8.61 8.1 0.0 466.4 0.0 0.32 0.0

Deli 225 1,370 11.61 29.94 18.29 53.8 26.9 337.1 0.0 0.29 18.9

Sales 2,325 14,177 11.61 29.94 18.29 5.4 0.0 3487.4 0.0 0.20 0.0

Produce 711 4,338 11.61 29.94 18.29 5.4 0.0 1067.0 0.0 0.27 0.0

Bakery 209 1,275 11.61 29.94 18.29 53.8 26.9 313.6 1179.9 0.34 18.9

Small Hotel 4,014 11,622

REARSTAIRSFLR1 20 67 9.95 6.46 0.0 0.0 0.0 0.0 0.58 0.0

CORRIDORFLR1 151 505 9.50 5.38 0.0 0.0 37.6 0.0 0.07 0.0

REARSTORAGEFLR1 20 67 4.98 8.61 0.0 0.0 0.0 0.0 0.58 0.0

FRONTLOUNGEFLR1 163 547 3.08 14.15 11.84 15.4 0.0 423.5 0.0 0.19 0.0

RESTROOMFLR1 33 109 32.61 11.82 9.68 10.8 0.0 0.0 200.0 0.13 0.0

MEETINGROOMFLR1 80 269 1.87 22.91 13.99 12.9 0.0 429.3 0.0 0.13 0.0

MECHANICALROOMFLR1 33 109 10.34 16.14 0.0 0.0 8.2 0.0 0.13 0.0

GUESTROOM101 33 109 21.74 20.68 11.84 14.3 0.0 14.2 0.0 0.13 0.2

GUESTROOM102 33 109 21.74 20.68 11.84 14.3 0.0 14.2 0.0 0.13 0.2

GUESTROOM103 33 109 21.74 20.68 11.84 14.3 0.0 14.2 0.0 0.13 0.2

GUESTROOM104 33 109 21.74 20.68 11.84 14.3 0.0 14.2 0.0 0.13 0.2

GUESTROOM105 33 109 21.74 20.68 11.84 14.3 0.0 14.2 0.0 0.13 0.2

EMPLOYEELOUNGEFLR1 33 109 2.96 17.73 12.91 77.2 0.0 88.1 0.0 0.13 0.0

LAUNDRYROOMFLR1 98 328 8.89 11.18 6.46 21.9 184.2 143.1 0.0 0.13 2.6

ELEVATORCOREFLR1 15 50 0.00 0.00 128.4 0.0 75.3 0.0 0.13 0.0

EXERCISECENTERFLR1 33 109 2.96 14.77 9.68 11.5 0.0 110.2 0.0 0.13 0.0

FRONTOFFICEFLR1 130 437 13.04 21.67 11.84 12.9 0.0 100.0 0.0 0.13 0.0

FRONTSTAIRSFLR1 20 67 9.95 6.46 0.0 0.0 0.0 0.0 0.58 0.0

FRONTSTORAGEFLR1 13 42 5.75 8.61 0.0 0.0 0.0 0.0 0.13 0.0

REARSTAIRSFLR2 20 55 8.77 6.46 0.0 0.0 0.0 0.0 0.58 0.0

CORRIDORFLR2 125 344 9.22 5.38 0.0 0.0 31.4 0.0 0.06 0.0

REARSTORAGEFLR2 20 55 4.39 8.61 0.0 0.0 0.0 0.0 0.58 0.0

GUESTROOM201 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.41 0.2

GUESTROOM202_205 130 358 21.74 18.77 11.84 14.3 0.0 56.6 0.0 0.13 0.2

GUESTROOM206_208 105 289 23.41 18.77 11.84 14.3 0.0 42.5 0.0 0.13 0.2

GUESTROOM209_212 130 358 21.74 18.77 11.84 14.3 0.0 56.6 0.0 0.13 0.2

GUESTROOM213 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.13 0.2

GUESTROOM214 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.13 0.2

GUESTROOM215_218 130 358 21.74 18.77 11.84 14.3 0.0 56.6 0.0 0.13 0.2

ELEVATORCOREFLR2 15 41 0.00 0.00 0.0 0.0 0.0 0.0 0.13 0.0

GUESTROOM219 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.13 0.2

GUESTROOM220_223 130 358 21.74 18.77 11.84 14.3 0.0 56.6 0.0 0.13 0.2

GUESTROOM224 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.13 0.2

FRONTSTORAGEFLR2 13 34 4.89 8.61 0.0 0.0 0.0 0.0 0.13 0.0

FRONTSTAIRSFLR2 20 55 8.77 6.46 0.0 0.0 0.0 0.0 0.58 0.0

REARSTAIRSFLR3 20 55 8.77 6.46 0.0 0.0 0.0 0.0 0.58 0.0

CORRIDORFLR3 125 344 9.22 5.38 0.0 0.0 31.4 0.0 0.06 0.0

REARSTORAGEFLR3 20 55 4.39 8.61 0.0 0.0 0.0 0.0 0.58 0.0

GUESTROOM301 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.41 0.2

GUESTROOM302_305 130 358 21.74 18.77 11.84 14.3 0.0 56.6 0.0 0.13 0.2

GUESTROOM306_308 105 289 23.41 18.77 11.84 14.3 0.0 42.5 0.0 0.13 0.2

GUESTROOM309_312 130 358 21.74 18.77 11.84 14.3 0.0 56.6 0.0 0.13 0.2

GUESTROOM313 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.13 0.2

GUESTROOM314 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.13 0.2

GUESTROOM315_318 130 358 21.74 18.77 11.84 14.3 0.0 56.6 0.0 0.13 0.2

ELEVATORCOREFLR3 15 41 0.00 0.00 0.0 0.0 0.0 0.0 0.13 0.0

GUESTROOM319 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.13 0.2

GUESTROOM320_323 130 358 21.74 18.77 11.84 14.3 0.0 56.6 0.0 0.13 0.2

GUESTROOM324 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.13 0.2

FRONTSTORAGEFLR3 13 34 4.89 8.61 0.0 0.0 0.0 0.0 0.13 0.0
69

Building Type/Zone

Area

m2

Vol.

m3

m2/

person

1989

Lights

Wm2

2004

Lights

Wm2

Elec.

Proc.

W/m2

Gas 

Proc. 

W/m2

Vent. 

L/s

Exhst 

L/s

Infil. 

ACH 

SWH 

L/h

FRONTSTAIRSFLR3 20 55 8.77 6.46 0.0 0.0 0.0 0.0 0.58 0.0

REARSTAIRSFLR4 20 55 4.39 6.46 0.0 0.0 0.0 0.0 0.98 0.0

CORRIDORFLR4 125 344 9.22 5.38 0.0 0.0 31.4 0.0 0.45 0.0

REARSTORAGEFLR4 20 55 4.39 8.61 0.0 0.0 0.0 0.0 0.98 0.0

GUESTROOM401 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.80 0.2

GUESTROOM402_405 130 358 21.74 18.77 11.84 14.3 0.0 56.6 0.0 0.53 0.2

GUESTROOM406_408 105 289 23.41 18.77 11.84 14.3 0.0 42.5 0.0 0.53 0.2

GUESTROOM409_412 130 358 21.74 18.77 11.84 14.3 0.0 56.6 0.0 0.53 0.2

GUESTROOM413 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.53 0.2

GUESTROOM414 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.53 0.2

GUESTROOM415_418 130 358 21.74 18.77 11.84 14.3 0.0 56.6 0.0 0.53 0.2

ELEVATORCOREFLR4 15 41 0.00 0.00 0.0 0.0 0.0 0.0 0.53 0.0

GUESTROOM419 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.53 0.2

GUESTROOM420_423 130 358 21.74 18.77 11.84 14.3 0.0 56.6 0.0 0.53 0.2

GUESTROOM424 33 89 21.74 18.77 11.84 14.3 0.0 14.2 0.0 0.53 0.2

FRONTSTORAGEFLR4 13 34 4.89 8.61 0.0 0.0 0.0 0.0 0.53 0.0

FRONTSTAIRSFLR4 20 55 8.77 6.46 0.0 0.0 0.0 0.0 0.98 0.0

Small Office 511 1,559

Core_ZN 150 456 18.58 19.48 10.76 10.76 0.0 80.5 0.0 0.00 11.4

Perimeter_ZN_1 113 346 18.58 19.48 10.76 10.76 0.0 61.1 0.0 0.62 0.0

Perimeter_ZN_2 67 205 18.58 19.48 10.76 10.76 0.0 36.2 0.0 0.66 0.0

Perimeter_ZN_3 113 346 18.58 19.48 10.76 10.76 0.0 61.1 0.0 0.62 0.0

Perimeter_ZN_4 67 205 18.58 19.48 10.76 10.76 0.0 36.2 0.0 0.66 0.0

Attic 568 720 0.00 0.00 0.0 0.0 0.0 0.0 1.00 0.0

Strip Mall 2,090 10,831

LGStore1 348 1,805 6.19 60.26 23.99 4.3 0.0 522.6 0.0 0.38 0.0

SMStore1 174 903 6.19 60.26 23.99 4.3 0.0 261.3 0.0 0.31 0.0

SMStore2 174 903 6.19 35.51 18.29 4.3 0.0 261.3 0.0 0.31 0.0

SMStore3 174 903 6.19 35.51 18.29 4.3 0.0 261.3 0.0 0.31 0.0

SMStore4 174 903 6.19 35.51 18.29 4.3 0.0 261.3 0.0 0.31 0.0

LGStore2 348 1,805 6.19 29.05 13.77 4.3 0.0 522.6 0.0 0.31 0.0

SMStore5 174 903 6.19 29.05 13.77 4.3 0.0 261.3 0.0 0.31 0.0

SMStore6 174 903 6.19 29.05 13.77 4.3 0.0 261.3 0.0 0.31 0.0

SMStore7 174 903 6.19 29.05 13.77 4.3 0.0 261.3 0.0 0.31 0.0

SMStore8 174 903 6.19 29.05 13.77 4.3 0.0 261.3 0.0 0.45 0.0

Warehouse 4,835 39,241

Office 237 1,011 47.38 21.69 11.84 8.1 0.0 50.0 0.0 0.16 0.0

Fine Storage 1,393 10,881 0.00 11.64 15.06 0.0 0.0 348.4 0.0 0.22 0.0

Bulk Storage 3,205 27,350 0.00 3.34 9.68 2.6 0.0 37758.1 0.0 0.19 0.0
70

Appendix B Schedules

Table B-1 Quick Service Restaurant Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

BLDG_EQUIP_SCH Weekday 0.1 0.1 0.1 0.1 0.1 0.1 0.35 0.35 0.25 0.25 0.35 0.35 0.35 0.35 0.25 0.25 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.25

Sat 0.1 0.1 0.1 0.1 0.1 0.1 0.35 0.35 0.25 0.25 0.35 0.35 0.35 0.35 0.25 0.25 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.25

SummerDesign 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.1 0.1 0.1 0.1 0.1 0.1 0.35 0.35 0.25 0.25 0.35 0.35 0.35 0.35 0.25 0.25 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.25

BLDG_LIGHT_SCH SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Weekday, Sat, Sun, 

Hol, Other 0.45 0.15 0.15 0.15 0.15 0.45 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9

BLDG_OCC_SCH WD 0.05 0 0 0 0 0.05 0.1 0.4 0.4 0.3 0.2 0.5 0.8 0.7 0.4 0.2 0.25 0.5 0.55 0.55 0.55 0.5 0.35 0.2

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sat, Sun, Hol, Other 0.05 0 0 0 0 0.05 0.05 0.3 0.3 0.3 0.2 0.45 0.6 0.5 0.35 0.3 0.3 0.3 0.55 0.55 0.55 0.5 0.35 0.2

GAS_EQUIP_SCH SummerDesign 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0.02 0.02 0.02 0.02 0.02 0.03 0.09 0.14 0.1 0.1 0.22 0.27 0.24 0.21 0.14 0.13 0.15 0.17 0.17 0.17 0.15 0.14 0.12 0.02

INFIL_HALF_ON_SCH WD, SummerDesign 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

Sat, WinterDesign 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

Sun, Hol, Other 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

Kitchen_Exhaust_SCH All 1 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Dual Zone Control Type Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

CLGSETP_KITCHEN_SCH WinterDesign 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30

Other 26 30 30 30 30 26 26 26 26 26 26 26 26 26 26 26 26 26 26 26 26 26 26 26

HTGSETP_KITCHEN_SCH SummerDesign 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

WinterDesign 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19

Other 19 15.6 15.6 15.6 15.6 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19

CLGSETP_SCH WinterDesign 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30

Other 24 30 30 30 30 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24

HTGSETP_SCH SummerDesign 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

Other 21 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

HVACOperationSchd All 1 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

MinOA_Sched All 1 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1
71

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

Kitchen_Case:1_WALKINFREEZER_

CaseCreditReduxSched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.2 0.2 0.2

Kitchen_Case:1_WALKINFREEZER_

CaseDefrost2aDaySched All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Kitchen_Case:1_WALKINFREEZER_

CaseDripDown2aDaySched All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Kitchen_Case:1_WALKINFREEZER_

WalkInStockingSched Tue, Fri 0 0 0 0 725 417 290 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0 0 0 0 125 117 90 0 0 0 0 0 0 0 0 0 0 0 0 125 117 90 0 0

Kitchen_Case:2_SELFCONTAINEDD

ISPLAYCASE_CaseStockingSched All 0 0 0 0 0 0 50 70 70 80 70 50 50 80 90 80 0 0 0 0 0 0 0 0

BLDG_SWH_SCH WD, SummerDesign 0.2 0 0 0 0 0 0.15 0.6 0.55 0.45 0.4 0.45 0.4 0.35 0.3 0.3 0.3 0.4 0.55 0.6 0.5 0.55 0.45 0.25

Sat, WinterDesign 0.2 0 0 0 0 0 0.15 0.15 0.15 0.5 0.45 0.5 0.5 0.45 0.4 0.4 0.35 0.4 0.55 0.55 0.5 0.55 0.4 0.3

Sun, Hol, Other 0.25 0 0 0 0 0 0.15 0.15 0.15 0.15 0.5 0.5 0.4 0.4 0.3 0.3 0.3 0.4 0.5 0.5 0.4 0.5 0.4 0.2

Kitchen Water Equipment Hot Supply 

Temp Sched All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49

Kitchen Water Equipment Latent fract 

sched All 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

Kitchen Water Equipment Sensible 

fract sched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

Kitchen Water Equipment Temp 

Sched All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49

PlantOnSched All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

SWHSys1 Water Heater Ambient 

Temperature Schedule Name All 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22

SWHSys1 Water Heater Setpoint 

Temperature Schedule Name All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1-Loop-Temp-Schedule All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60
72

Table B-2 Hospital Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Kitchen_Exhaust_SCH WD 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0

SummerDesign 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0

WinterDesign 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0 0 0

Sats 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

ADMIN_EQUIP_SCH WD 0.3 0.3 0.3 0.3 0.5 0.5 1 1 1 1 1 1 1 1 1 1 1 1 0.5 0.5 0.3 0.3 0.3 0.3

SummerDesign 0.3 0.3 0.3 0.3 0.5 0.5 1 1 1 1 1 1 1 1 1 1 1 1 0.5 0.5 0.3 0.3 0.3 0.3

WinterDesign 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3

Sat 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.5 0.5 0.8 0.8 0.8 0.8 0.8 0.8 0.5 0.5 0.5 0.5 0.5 0.3 0.3 0.3 0.3

Other 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.3 0.3 0.3 0.3 0.3 0.3 0.3

ADMIN_LIGHT_SCH WD 0.1 0.1 0.1 0.1 0.3 0.3 0.6 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.6 0.6 0.3 0.3 0.1 0.1

SummerDesign 0.1 0.1 0.1 0.1 0.3 0.3 0.6 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.6 0.6 0.3 0.3 0.1 0.1

WinterDesign 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.3 0.3 0.4 0.4 0.4 0.4 0.4 0.4 0.3 0.3 0.3 0.3 0.3 0.1 0.1 0.1 0.1

Sat 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.3 0.3 0.4 0.4 0.4 0.4 0.4 0.4 0.3 0.3 0.3 0.3 0.3 0.1 0.1 0.1 0.1

Other 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.05 0.05 0.05 0.05 0.05 0.05 0.05

ADMIN_OCC_SCH WD 0.05 0.05 0.05 0.05 0.2 0.2 0.5 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.5 0.5 0.2 0.2 0.05 0.05

SummerDesign 0.05 0.05 0.05 0.05 0.2 0.2 0.5 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.5 0.5 0.2 0.2 0.05 0.05

WinterDesign 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.2 0.2 0.3 0.3 0.3 0.3 0.3 0.3 0.2 0.2 0.2 0.2 0.2 0.05 0.05 0.05 0.05

Sat 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.2 0.2 0.3 0.3 0.3 0.3 0.3 0.3 0.2 0.2 0.2 0.2 0.2 0.05 0.05 0.05 0.05

Sun, Hol, Other 0 0 0 0 0 0 0 0 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0 0 0 0 0 0 0

BLDG_ELEVATORS WD, SummerDesign 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.5 0.75 1 1 1 0.75 1 1 1 1 1 0.52 0.52 0.52 0.28 0.2 0.2

Sat, WinterDesign 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.46 0.7 0.7 0.7 0.51 0.51 0.51 0.51 0.51 0.25 0.2 0.2 0.2 0.2 0.2 0.2

Other 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

BLDG_LIGHT_SCH WD 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.5 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.1

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sat 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.1 0.1 0.1 0.1 0.1 0.1

Other 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

CRITICAL_EQUIP_SCH WD 0.5 0.5 0.5 0.5 0.5 0.5 1 1 1 1 1 1 1 1 1 1 1 1 0.8 0.8 0.5 0.5 0.5 0.5

SummerDesign 0.5 0.5 0.5 0.5 0.5 0.5 1 1 1 1 1 1 1 1 1 1 1 1 0.8 0.8 0.5 0.5 0.5 0.5

WinterDesign 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3

Sat 0.5 0.5 0.5 0.5 0.5 0.5 1 1 1 1 1 1 1 1 1 1 1 1 0.8 0.8 0.5 0.5 0.5 0.5

Sun, Hol, Other 0.5 0.5 0.5 0.5 0.5 0.5 1 1 1 1 1 1 1 1 1 1 1 1 0.8 0.8 0.5 0.5 0.5 0.5

CRITICAL_LIGHT_SCH WD 0.5 0.5 0.5 0.5 0.7 0.7 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.7 0.7 0.7 0.5 0.5

SummerDesign 0.5 0.5 0.5 0.5 0.7 0.7 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.7 0.7 0.7 0.5 0.5

WinterDesign 0.5 0.5 0.5 0.5 0.7 0.7 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.7 0.7 0.7 0.5 0.5

Sat 0.5 0.5 0.5 0.5 0.7 0.7 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.7 0.7 0.7 0.5 0.5

Other 0.5 0.5 0.5 0.5 0.7 0.7 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.7 0.7 0.7 0.5 0.5

CRITICAL_OCC_SCH WD 0.4 0.4 0.4 0.4 0.65 0.65 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.65 0.65 0.65 0.65 0.4 0.4

SummerDesign 0.4 0.4 0.4 0.4 0.65 0.65 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.65 0.65 0.65 0.65 0.4 0.4

WinterDesign 0.4 0.4 0.4 0.4 0.65 0.65 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.65 0.65 0.65 0.65 0.4 0.4

Sat 0.4 0.4 0.4 0.4 0.65 0.65 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.65 0.65 0.65 0.65 0.4 0.4

Other 0.4 0.4 0.4 0.4 0.65 0.65 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.65 0.65 0.65 0.65 0.4 0.4
73

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

INFIL_QUARTER_ON_SCH WD 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25

Sat 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25

SummerDesign, 

WinterDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Other 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25

Kitchen_Elec_Equip_SCH Weekday 0.1 0.1 0.1 0.1 0.1 0.1 0.25 0.35 0.35 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.25 0.25

Sat 0.1 0.1 0.1 0.1 0.1 0.1 0.25 0.35 0.35 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.25 0.25

SummerDesign 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0.1 0.1 0.1 0.1 0.1 0.1 0.25 0.35 0.35 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.25 0.25

Kitchen_Gas_Equip_SCH WD, Sat 0.02 0.02 0.02 0.02 0.02 0.05 0.1 0.15 0.2 0.15 0.25 0.25 0.25 0.2 0.15 0.2 0.3 0.3 0.3 0.2 0.2 0.15 0.1 0.05

SummerDesign 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0.02 0.02 0.02 0.02 0.02 0.05 0.1 0.15 0.2 0.15 0.25 0.25 0.25 0.2 0.15 0.2 0.3 0.3 0.3 0.2 0.2 0.15 0.1 0.05

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

ADMIN_CLGSETP_SCH WD 25 25 25 25 25 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 25 25 25 25 25 25

SummerDesign 25 25 25 25 25 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 25 25 25 25 25 25

WinterDesign 25 25 25 25 25 25 25 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 25 25 25 25 25 25 25 25 25

Sats 25 25 25 25 25 25 25 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 25 25 25 25 25 25 25 25 25

Other 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25

ADMIN_HTGSETP_SCH WD 18.3 18.3 18.3 18.3 18.3 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 18.3 18.3 18.3 18.3 18.3 18.3

SummerDesign 18.3 18.3 18.3 18.3 18.3 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 18.3 18.3 18.3 18.3 18.3 18.3

WinterDesign 18.3 18.3 18.3 18.3 18.3 18.3 18.3 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3

Sats 18.3 18.3 18.3 18.3 18.3 18.3 18.3 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3

Other 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3

Kitchen_CLGSETP_SCH WD 30 30 30 30 30 26 26 26 26 26 26 26 26 26 26 26 26 26 30 30 30 30 30 30

SummerDesign 30 30 30 30 30 26 26 26 26 26 26 26 26 26 26 26 26 26 30 30 30 30 30 30

WinterDesign 30 30 30 30 30 30 30 26 26 26 26 26 26 26 26 30 30 30 30 30 30 30 30 30

Sats 30 30 30 30 30 30 30 26 26 26 26 26 26 26 26 30 30 30 30 30 30 30 30 30

Other 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30

Kitchen_HTGSETP_SCH WD 15.6 15.6 15.6 15.6 15.6 19 19 19 19 19 19 19 19 19 19 19 19 19 15.6 15.6 15.6 15.6 15.6 15.6

SummerDesign 15.6 15.6 15.6 15.6 15.6 19 19 19 19 19 19 19 19 19 19 19 19 19 15.6 15.6 15.6 15.6 15.6 15.6

WinterDesign 15.6 15.6 15.6 15.6 15.6 15.6 15.6 19 19 19 19 19 19 19 19 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

Sats 15.6 15.6 15.6 15.6 15.6 15.6 15.6 19 19 19 19 19 19 19 19 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

Other 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

CRITICAL_CLGSETP_SCH All 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2

CRITICAL_HTGSETP_SCH All 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1

OR_CLGSETP_SCH All 22.2 22.2 22.2 22.2 22.2 22.2 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 22.2 22.2 22.2 22.2 22.2 22.2 22.2

OR_HTGSETP_SCH All 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3

Dual Zone Control Type Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

MaxRelHumSetSch All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60
74

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

MinRelHumSetSch All 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40

CAV_SAT_SCH All 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1

Heating-Supply-Air-Temp-Sch All 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16

Seasonal-Reset-Supply-Air-TempSch All 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1

HVACOperationSchd All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

CAV_OAminFracSchedule All 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33

VAV_OAminFracSchedule All 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25

CW-Loop-Temp-Schedule All 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7

HW-Loop-Temp-Schedule All 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2

PlantOnSched All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Kitchen_Flr_5_Case:1_WALKINFRE

EZER_CaseCreditReduxSched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.2 0.2 0.2

Kitchen_Flr_5_Case:1_WALKINFRE

EZER_CaseDefrost2aDaySched All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Kitchen_Flr_5_Case:1_WALKINFRE

EZER_CaseDripDown2aDaySched All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Kitchen_Flr_5_Case:1_WALKINFRE

EZER_WalkInStockingSched Tue, Fri 0 0 0 0 725 417 290 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0 0 0 0 125 117 90 0 0 0 0 0 0 0 0 0 0 0 0 125 117 90 0 0

Kitchen_Flr_5_Case:2_SELFCONT

AINEDDISPLAYCASE_CaseStockin

gSched All 0 0 0 0 0 0 50 70 70 80 70 50 50 80 90 80 0 0 0 0 0 0 0 0

BLDG_SWH_EXTD_SCH WD, SummerDesign 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.5 0.58 0.66 0.78 0.82 0.71 0.82 0.78 0.74 0.63 0.41 0.35 0.35 0.35 0.3 0.3 0.3

Other 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.4 0.5 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.5 0.3 0.3 0.3 0.3 0.3 0.3

BLDG_SWH_SCH WD, SummerDesign 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.17 0.58 0.66 0.78 0.82 0.71 0.82 0.78 0.74 0.63 0.41 0.18 0.18 0.18 0.1 0.01 0.01

Sat, WinterDesign 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.2 0.28 0.3 0.3 0.24 0.24 0.23 0.23 0.23 0.1 0.01 0.01 0.01 0.01 0.01 0.01

Sun, Hol, Other 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01

Water Equipment Hot Supply Temp 

Sched All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49

Water Equipment Latent fract sched All 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

Water Equipment Sensible fract 

sched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

Water Equipment Temp Sched All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49

SWHSys1 Water Heater Ambient 

Temperature Schedule Name All 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22

SWHSys1 Water Heater Setpoint 

Temperature Schedule Name All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1-Loop-Temp-Schedule All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60
75

Table B-3 Large Hotel Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

BLDG_ELEVATORS All 0.05 0.05 0.05 0.05 0.1 0.2 0.4 0.5 0.5 0.35 0.15 0.15 0.15 0.15 0.15 0.15 0.35 0.5 0.5 0.4 0.4 0.3 0.2 0.1

BLDG_EQUIP_SCH WD 0.3 0.25 0.2 0.2 0.2 0.3 0.5 0.6 0.5 0.5 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.7 0.9 0.95 0.9 0.7 0.4

Sat 0.3 0.3 0.2 0.2 0.2 0.2 0.4 0.4 0.5 0.5 0.4 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.7 0.8 0.8 0.8 0.7 0.4

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.4 0.4 0.3 0.3 0.3 0.3 0.4 0.5 0.5 0.4 0.4 0.4 0.4 0.3 0.3 0.3 0.3 0.3 0.6 0.8 0.9 0.7 0.6 0.4

BLDG_LIGHT_SCH WD 0.2 0.15 0.1 0.1 0.1 0.2 0.4 0.5 0.4 0.4 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.6 0.8 0.9 0.8 0.6 0.3

Sat 0.2 0.2 0.1 0.1 0.1 0.1 0.3 0.3 0.4 0.4 0.3 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.6 0.7 0.7 0.7 0.6 0.3

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.3 0.3 0.2 0.2 0.2 0.2 0.3 0.4 0.4 0.3 0.3 0.3 0.3 0.2 0.2 0.2 0.2 0.2 0.5 0.7 0.8 0.6 0.5 0.3

BLDG_OCC_SCH WD 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.4 0.4 0.2 0.2 0.2 0.2 0.2 0.2 0.3 0.5 0.5 0.5 0.7 0.7 0.8 0.9 0.9

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Sat 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.5 0.5 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.5 0.6 0.6 0.6 0.7 0.7 0.7

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.5 0.5 0.5 0.3 0.3 0.2 0.2 0.2 0.3 0.4 0.4 0.6 0.6 0.8 0.8 0.8

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

GuestRoom_Eqp_Sch WD 0.2 0.2 0.2 0.2 0.2 0.2 0.62 0.9 0.43 0.43 0.26 0.26 0.26 0.26 0.26 0.26 0.26 0.51 0.51 0.49 0.66 0.7 0.35 0.2

Sat, Sun, Hol 0.2 0.2 0.2 0.2 0.2 0.2 0.3 0.62 0.9 0.62 0.29 0.29 0.29 0.29 0.29 0.29 0.29 0.43 0.51 0.49 0.66 0.7 0.35 0.2

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

GuestRoom_Ltg_Sch_Base WD 0.22 0.17 0.11 0.11 0.11 0.22 0.44 0.56 0.44 0.44 0.28 0.28 0.28 0.28 0.28 0.28 0.28 0.28 0.67 0.89 1 0.89 0.67 0.33

Sat, Sun, Hol 0.26 0.26 0.11 0.11 0.11 0.11 0.41 0.41 0.56 0.56 0.41 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.85 1 1 1 0.85 0.41

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

GuestRoom_Occ_Sch WD 0.65 0.65 0.65 0.65 0.65 0.65 0.5 0.28 0.28 0.13 0.13 0.13 0.13 0.13 0.13 0.2 0.35 0.35 0.35 0.5 0.5 0.58 0.65 0.65

Sat, Sun, Hol 0.65 0.65 0.65 0.65 0.65 0.65 0.5 0.34 0.34 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.34 0.35 0.65 0.65 0.5 0.5 0.5

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

INFIL_QUARTER_ON_SCH All 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25

Kitchen_Elec_Equip_SCH Weekday 0.1 0.1 0.1 0.1 0.1 0.1 0.25 0.35 0.35 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.25 0.25

Sat 0.1 0.1 0.1 0.1 0.1 0.1 0.25 0.35 0.35 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.25 0.25

SummerDesign 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.1 0.1 0.1 0.1 0.1 0.1 0.25 0.35 0.35 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.25 0.25
76

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

Kitchen_Gas_Equip_SCH WD, Sat 0.02 0.02 0.02 0.02 0.02 0.05 0.1 0.15 0.2 0.15 0.25 0.25 0.25 0.2 0.15 0.2 0.3 0.3 0.3 0.2 0.2 0.15 0.1 0.05

SummerDesign 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.02 0.02 0.02 0.02 0.02 0.05 0.1 0.15 0.2 0.15 0.25 0.25 0.25 0.2 0.15 0.2 0.3 0.3 0.3 0.2 0.2 0.15 0.1 0.05

LaundryRoom_Eqp_Elec_Sch WD, Sat, Sun, Hol 0 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0 0

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

LaundryRoom_Eqp_Gas_Sch WD, Sat, Sun, Hol 0 0 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Lobby_Occ_Sch WD 0.1 0.1 0.1 0.1 0.1 0.3 0.7 0.7 0.7 0.7 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.4 0.2 0.2 0.2 0.2 0.1 0.1

Sat, Sun, Hol 0.1 0.1 0.1 0.1 0.1 0.1 0.3 0.7 0.7 0.7 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.1 0.1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Kitchen_Exhaust_SCH All 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

CLGSETP_SCH All 30 30 30 30 30 30 30 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24

HTGSETP_SCH All 16 16 16 16 16 16 16 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

Corr_CLGSETP_SCH All 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30

Corr_HTGSETP_SCH All 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16

Guest_CLGSETP_SCH All 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24

Guest_HTGSETP_SCH All 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

Kitchen_CLGSETP_SCH All 30 30 30 30 30 30 30 26 26 26 26 26 26 26 26 26 26 26 26 26 26 26 26 26

Kitchen_HTGSETP_SCH All 16 16 16 16 16 16 16 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19

Dual Zone Control Type Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

HVACOperationSchd All 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

MinOA_Sched All 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Seasonal-Reset-Supply-Air-Temp-Sch All 13 13 13 13 13 13 13 13 13 13 13 13 13 13 13 13 13 13 13 13 13 13 13 13

CW-Loop-Temp-Schedule All 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7

HW-Loop-Temp-Schedule All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

PlantOnSched All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Kitchen_Flr_6_Case:1_WALKINFREEZER_

CaseCreditReduxSched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.2 0.2 0.2

Kitchen_Flr_6_Case:1_WALKINFREEZER_

CaseDefrost2aDaySched All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Kitchen_Flr_6_Case:1_WALKINFREEZER_

CaseDripDown2aDaySched All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Kitchen_Flr_6_Case:1_WALKINFREEZER_

WalkInStockingSched Tue, Fri 0 0 0 0 725 417 290 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0 0 0 0 125 117 90 0 0 0 0 0 0 0 0 0 0 0 0 125 117 90 0 0

Kitchen_Flr_6_Case:2_SELFCONTAINEDD

ISPLAYCASE_CaseStockingSched All 0 0 0 0 0 0 50 70 70 80 70 50 50 80 90 80 0 0 0 0 0 0 0 0
77

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

Kitchen_SWH_SCH WD, SummerDesign 0.2 0.15 0.15 0.15 0.2 0.25 0.5 0.6 0.55 0.45 0.4 0.45 0.4 0.35 0.3 0.3 0.3 0.4 0.55 0.6 0.5 0.55 0.45 0.25

Sat, WinterDesign 0.2 0.15 0.15 0.15 0.2 0.25 0.4 0.5 0.5 0.5 0.45 0.5 0.5 0.45 0.4 0.4 0.35 0.4 0.55 0.55 0.5 0.55 0.4 0.3

Sun, Hol, Other 0.25 0.2 0.2 0.2 0.2 0.3 0.5 0.5 0.5 0.55 0.5 0.5 0.4 0.4 0.3 0.3 0.3 0.4 0.5 0.5 0.4 0.5 0.4 0.2

GuestRoom_SWH_Sch WD 0.2 0.15 0.15 0.15 0.2 0.35 0.6 0.8 0.55 0.4 0.3 0.2 0.2 0.2 0.2 0.2 0.2 0.3 0.55 0.4 0.4 0.6 0.45 0.25

Other 0.2 0.15 0.15 0.15 0.2 0.25 0.35 0.6 0.8 0.55 0.4 0.3 0.2 0.2 0.2 0.2 0.2 0.25 0.3 0.4 0.4 0.4 0.6 0.35

LaundryRoom_SWH_Sch All 0 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0 0

Water Equipment Latent fract sched All 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

Water Equipment Sensible fract sched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

Guest Room Water Equipment Hot Supply 

Temp Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

Guest Room Water Equipment Temp Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

Kitchen Water Equipment Hot Supply Temp 

Sched All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49

Kitchen Water Equipment Temp Sched All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49

Laundry Water Equipment Hot Supply Temp 

Sched All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

Laundry Water Equipment Temp Sched All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1 Water Heater Ambient 

Temperature Schedule Name All 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22

SWHSys1 Water Heater Setpoint 

Temperature Schedule Name All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1-Loop-Temp-Schedule All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60
78

Table B-4 Large Office Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

BLDG_ELEVATORS All 0.05 0.05 0.05 0.05 0.1 0.2 0.4 0.5 0.5 0.35 0.15 0.15 0.15 0.15 0.15 0.15 0.35 0.5 0.5 0.4 0.4 0.3 0.2 0.1

INFIL_QUARTER_ON_SCH WD, SummerDesign 1 1 1 1 1 1 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 1 1

Sat, WinterDesign 1 1 1 1 1 1 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 1 1 1 1 1 1

Sun, Hol, Other 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

BLDG_OCC_SCH SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0.05 0.05

WD 0 0 0 0 0 0 0.1 0.2 0.95 0.95 0.95 0.95 0.5 0.95 0.95 0.95 0.95 0.7 0.4 0.4 0.1 0.1 0.05 0.05

Sat 0 0 0 0 0 0 0.1 0.1 0.5 0.5 0.5 0.5 0.5 0.5 0.1 0.1 0.1 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_LIGHT_SCH WD 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.3 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.5 0.5 0.3 0.3 0.1 0.05

Sat 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.5 0.5 0.5 0.5 0.5 0.5 0.15 0.15 0.15 0.05 0.05 0.05 0.05 0.05 0.05 0.05

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

BLDG_EQUIP_SCH WD 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.9 0.9 0.9 0.9 0.8 0.9 0.9 0.9 0.9 0.8 0.6 0.6 0.5 0.5 0.4 0.4

Sat 0.3 0.3 0.3 0.3 0.3 0.3 0.4 0.4 0.5 0.5 0.5 0.5 0.5 0.5 0.35 0.35 0.35 0.3 0.3 0.3 0.3 0.3 0.3 0.3

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

CLGSETP_SCH WD, SummerDesign 26.7 26.7 26.7 26.7 26.7 26.7 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 26.7 26.7

Sat 26.7 26.7 26.7 26.7 26.7 26.7 24 24 24 24 24 24 24 24 24 24 24 24 26.7 26.7 26.7 26.7 26.7 26.7

WinterDesign 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7

Other 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7

HTGSETP_SCH WD 15.6 15.6 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 15.6 15.6

SummerDesign 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

Sat 15.6 15.6 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 21 15.6 15.6 15.6 15.6 15.6 15.6

WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

Other 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

Seasonal-Reset-Supply-Air-Temp-Sch All 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8

MinOA_MotorizedDamper_Sched WD, SummerDesign 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0

Sat, WinterDesign 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Dual Zone Control Type Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

HVACOperationSchd WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0

Sat, WinterDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

CW-Loop-Temp-Schedule All 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7

HW-Loop-Temp-Schedule All 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2
79

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

BLDG_SWH_SCH WD, SummerDesign 0.05 0.05 0.05 0.05 0.05 0.08 0.07 0.19 0.35 0.38 0.39 0.47 0.57 0.54 0.34 0.33 0.44 0.26 0.21 0.15 0.17 0.08 0.05 0.05

Sat, WinterDesign 0.05 0.05 0.05 0.05 0.05 0.08 0.07 0.11 0.15 0.21 0.19 0.23 0.2 0.19 0.15 0.13 0.14 0.07 0.07 0.07 0.07 0.09 0.05 0.05

Other 0.04 0.04 0.04 0.04 0.04 0.07 0.04 0.04 0.04 0.04 0.04 0.06 0.06 0.09 0.06 0.04 0.04 0.04 0.04 0.04 0.04 0.07 0.04 0.04

Water Equipment Latent fract sched All 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

Water Equipment Sensible fract sched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

SWHSys1 Water Heater Ambient 

Temperature Schedule Name All 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22

Water Equipment Temp Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

Water Equipment Hot Supply Temp 

Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

SWHSys1 Water Heater Setpoint 

Temperature Schedule Name All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1-Loop-Temp-Schedule All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60
80

Table B-5 Medium Office Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

BLDG_ELEVATORS WD, SummerDesign 0 0 0 0 0 0 0 0.35 0.69 0.43 0.37 0.43 0.58 0.48 0.37 0.37 0.46 0.62 0.12 0.04 0.04 0 0 0

Sat, WinterDesign 0 0 0 0 0 0 0 0.16 0.14 0.21 0.18 0.25 0.21 0.13 0.08 0.04 0.05 0.06 0 0 0 0 0 0

Sun, Hol, Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_OCC_SCH SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0.05 0.05

WD 0 0 0 0 0 0 0.1 0.2 0.95 0.95 0.95 0.95 0.5 0.95 0.95 0.95 0.95 0.7 0.4 0.4 0.1 0.1 0.05 0.05

Sat 0 0 0 0 0 0 0.1 0.1 0.5 0.5 0.5 0.5 0.5 0.5 0.1 0.1 0.1 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_LIGHT_SCH WD 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.3 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.5 0.5 0.3 0.3 0.1 0.05

Sat 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.5 0.5 0.5 0.5 0.5 0.5 0.15 0.15 0.15 0.05 0.05 0.05 0.05 0.05 0.05 0.05

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

BLDG_EQUIP_SCH WD 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.9 0.9 0.9 0.9 0.8 0.9 0.9 0.9 0.9 0.8 0.6 0.6 0.5 0.5 0.4 0.4

Sat 0.3 0.3 0.3 0.3 0.3 0.3 0.4 0.4 0.5 0.5 0.5 0.5 0.5 0.5 0.35 0.35 0.35 0.3 0.3 0.3 0.3 0.3 0.3 0.3

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

INFIL_QUARTER_ON_SCH WD, SummerDesign 1 1 1 1 1 1 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 1 1

Sat, WinterDesign 1 1 1 1 1 1 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 1 1 1 1 1 1

Sun, Hol, Other 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Dual Zone Control Type 

Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

CLGSETP_SCH WD, SummerDesign 26.7 26.7 26.7 26.7 26.7 26.7 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 26.7 26.7

Sat 26.7 26.7 26.7 26.7 26.7 26.7 24 24 24 24 24 24 24 24 24 24 24 24 26.7 26.7 26.7 26.7 26.7 26.7

WinterDesign 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7

Other 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7

HTGSETP_SCH WD 15.6 15.6 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 15.6 15.6

SummerDesign 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

Sat 15.6 15.6 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 21 15.6 15.6 15.6 15.6 15.6 15.6

WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

Other 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

HVACOperationSchd WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0

Sat, WinterDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

MinOA_MotorizedDamper_S

ched WD, SummerDesign 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0

Sat, WinterDesign 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0
81

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Seasonal-Reset-Supply-AirTemp-Sch All 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8

BLDG_SWH_SCH WD, SummerDesign 0.05 0.05 0.05 0.05 0.05 0.08 0.07 0.19 0.35 0.38 0.39 0.47 0.57 0.54 0.34 0.33 0.44 0.26 0.21 0.15 0.17 0.08 0.05 0.05

Sat, WinterDesign 0.05 0.05 0.05 0.05 0.05 0.08 0.07 0.11 0.15 0.21 0.19 0.23 0.2 0.19 0.15 0.13 0.14 0.07 0.07 0.07 0.07 0.09 0.05 0.05

Sun, Hol, Other 0.04 0.04 0.04 0.04 0.04 0.07 0.04 0.04 0.04 0.04 0.04 0.06 0.06 0.09 0.06 0.04 0.04 0.04 0.04 0.04 0.04 0.07 0.04 0.04

Water Equipment Latent 

fract sched All 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

Water Equipment Sensible 

fract sched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

Water Equipment Hot Supply 

Temp Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

Water Equipment Temp 

Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

SWHSys1 Water Heater 

Ambient Temperature 

Schedule Name All 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22

SWHSys1 Water Heater 

Setpoint Temperature 

Schedule Name All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1-Loop-TempSchedule All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

BLDG_ELEVATORS WD, SummerDesign 0 0 0 0 0 0 0 0.35 0.69 0.43 0.37 0.43 0.58 0.48 0.37 0.37 0.46 0.62 0.12 0.04 0.04 0 0 0

Sat, WinterDesign 0 0 0 0 0 0 0 0.16 0.14 0.21 0.18 0.25 0.21 0.13 0.08 0.04 0.05 0.06 0 0 0 0 0 0

Sun, Hol, Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_OCC_SCH SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0.05 0.05

WD 0 0 0 0 0 0 0.1 0.2 0.95 0.95 0.95 0.95 0.5 0.95 0.95 0.95 0.95 0.7 0.4 0.4 0.1 0.1 0.05 0.05

Sat 0 0 0 0 0 0 0.1 0.1 0.5 0.5 0.5 0.5 0.5 0.5 0.1 0.1 0.1 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_LIGHT_SCH WD 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.3 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.5 0.5 0.3 0.3 0.1 0.05

Sat 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.5 0.5 0.5 0.5 0.5 0.5 0.15 0.15 0.15 0.05 0.05 0.05 0.05 0.05 0.05 0.05

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

BLDG_EQUIP_SCH WD 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.9 0.9 0.9 0.9 0.8 0.9 0.9 0.9 0.9 0.8 0.6 0.6 0.5 0.5 0.4 0.4

Sat 0.3 0.3 0.3 0.3 0.3 0.3 0.4 0.4 0.5 0.5 0.5 0.5 0.5 0.5 0.35 0.35 0.35 0.3 0.3 0.3 0.3 0.3 0.3 0.3

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

INFIL_QUARTER_ON_SCH WD, SummerDesign 1 1 1 1 1 1 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 1 1

Sat, WinterDesign 1 1 1 1 1 1 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 1 1 1 1 1 1

Sun, Hol, Other 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1
82

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Dual Zone Control Type 

Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

CLGSETP_SCH WD, SummerDesign 26.7 26.7 26.7 26.7 26.7 26.7 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 26.7 26.7

Sat 26.7 26.7 26.7 26.7 26.7 26.7 24 24 24 24 24 24 24 24 24 24 24 24 26.7 26.7 26.7 26.7 26.7 26.7

WinterDesign 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7

Other 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7
83

Table B-6 Midrise Apartment Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

BLDG_ELEVATORS All 0.05 0.05 0.05 0.05 0.1 0.2 0.4 0.5 0.5 0.35 0.15 0.15 0.15 0.15 0.15 0.15 0.35 0.5 0.5 0.4 0.4 0.3 0.2 0.1

INFIL_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

OFFICE_INFIL_SCH WD 1 1 1 1 1 1 1 1 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 1 1 1 1 1 1 1

Other 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

APT_OCC_SCH All 1 1 1 1 1 1 1 0.85 0.39 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.3 0.52 0.87 0.87 0.87 1 1 1

OFF_OCC_SCH

WD, SummerDesign, 

WinterDesign 0 0 0 0 0 0 0 0 1 1 1 1 0.5 1 1 1 1 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

APT_LIGHT_SCH All 0.07 0.07 0.07 0.07 0.19 0.39 0.44 0.39 0.17 0.12 0.12 0.12 0.12 0.12 0.12 0.21 0.44 0.62 0.83 0.99 1 0.69 0.38 0.16

OFF_LIGHT_SCH WD, SummerDesign 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.9 0.9 0.9 0.9 0.8 0.9 0.9 0.9 0.9 0.18 0.18 0.18 0.18 0.18 0.18 0.18

Other 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18

COR_LIGHT_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

APT_EQP_SCH All 0.45 0.41 0.39 0.38 0.38 0.43 0.54 0.65 0.66 0.67 0.69 0.7 0.69 0.66 0.65 0.68 0.8 1 1 0.93 0.89 0.85 0.71 0.58

OFF_EQP_SCH WD, SummerDesign 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.5 1 1 1 1 0.94 1 1 1 1 0.5 0.33 0.33 0.33 0.33 0.33 0.33

Other 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

UnitHeater_ClgSP_Sch All 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40

UnitHeater_HtgSP_Sch All 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

APT_CLGSETP_SCH All 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9

APT_HTGSETP_SCH All 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1

OFF_HTGSETP_SCH WD, WinterDesign 15.6 15.6 15.6 15.6 15.6 15.6 15.6 18.3 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 18.3 15.6 15.6 15.6 15.6 15.6 15.6

Other 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

OFF_CLGSETP_SCH WD, SummerDesign 29.4 29.4 29.4 29.4 29.4 29.4 29.4 26.7 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 23.9 26.7 29.4 29.4 29.4 29.4 29.4 29.4

Other 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4 29.4

Dual Zone Control Type Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

Apt_Operation All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Office_Operation

WD, SummerDesign, 

WinterDesign 0 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

MinOA_Sched All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Apartment Water Equipment 

Latent fract sched All 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

Apartment Water Equipment 

Sensible fract sched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

Apartment Water Equipment 

Temp Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

Apartment Water Equipment Hot 

Supply Temp Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

SWHSys1 Water Heater Setpoint All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60
84

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

Temperature Schedule Name

SWHSys1 Water Heater Ambient 

Temperature Schedule Name All 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22

SWHSys1-Loop-Temp-Schedule All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

APT_DHW_SCH All 0.08 0.04 0.01 0.01 0.04 0.27 0.94 1 0.96 0.84 0.76 0.61 0.53 0.47 0.41 0.47 0.55 0.73 0.86 0.82 0.75 0.61 0.53 0.29
85

Table B-7 Outpatient Health Care Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

BLDG_ELEVATORS WD, SummerDesign 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.5 0.75 1 1 1 0.75 1 1 1 1 1 0.52 0.52 0.52 0.28 0.05 0.05

Sat 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.4 0.46 0.7 0.7 0.7 0.51 0.51 0.51 0.51 0.51 0.25 0.05 0.05 0.05 0.05 0.05 0.05

Other 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

BLDG_EQUIP_SCH WD, SummerDesign 0.3 0.3 0.3 0.3 0.5 0.5 1 1 1 1 1 1 1 1 1 1 1 1 0.5 0.5 0.3 0.3 0.3 0.3

Sat 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.5 0.5 0.8 0.8 0.8 0.8 0.8 0.8 0.5 0.5 0.5 0.5 0.5 0.3 0.3 0.3 0.3

Other 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.3 0.3 0.3 0.3 0.3 0.3 0.3

BLDG_LIGHT_SCH WD, SummerDesign 0.1 0.1 0.1 0.1 0.3 0.3 0.6 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.6 0.6 0.3 0.3 0.1 0.1

Sat 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.3 0.3 0.4 0.4 0.4 0.4 0.4 0.4 0.3 0.3 0.3 0.3 0.3 0.1 0.1 0.1 0.1

Other 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.05 0.05 0.05 0.05 0.05 0.05 0.05

BLDG_OCC_SCH WD, SummerDesign 0.05 0.05 0.05 0.05 0.2 0.2 0.5 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.5 0.5 0.2 0.2 0.05 0.05

Sat 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.2 0.2 0.3 0.3 0.3 0.3 0.3 0.3 0.2 0.2 0.2 0.2 0.2 0.05 0.05 0.05 0.05

Other 0 0 0 0 0 0 0 0 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0 0 0 0 0 0 0

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

INFIL_SCH

SummerDesign, 

WinterDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Other 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

RADIOLOGY_EQUIP_SCH

WD, Sat, 

SummerDesign 0.01 0.01 0.01 0.01 0.01 0.01 0.96 0.96 0.96 0.96 0.96 0.96 0.96 0.96 0.96 0.96 0.96 0.96 0.01 0.01 0.01 0.01 0.01 0.01

Other 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01

OR_CLGSETP_SCH All 22.2 22.2 22.2 22.2 22.2 22.2 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 22.2 22.2 22.2 22.2 22.2 22.2 22.2

OR_HTGSETP_SCH All 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3

CLGSETP_SCH WD, SummerDesign 25 25 25 25 25 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 25 25 25 25 25 25

Sat, WinterDesign 25 25 25 25 25 25 25 22.2 22.2 22.2 22.2 22.2 22.2 22.2 22.2 25 25 25 25 25 25 25 25 25

Other 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25 25

HTGSETP_SCH WD, SummerDesign 18.3 18.3 18.3 18.3 18.3 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 18.3 18.3 18.3 18.3 18.3 18.3

Sat, WinterDesign 18.3 18.3 18.3 18.3 18.3 18.3 18.3 21.1 21.1 21.1 21.1 21.1 21.1 21.1 21.1 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3

Other 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3 18.3

Dual Zone Control Type 

Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

MaxRelHumSetSch All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

MinRelHumSetSch All 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40

AHU-1_MinOAFracSchedule All 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.33

AHU-1_Fan_Sch WD, Sat 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0

SummerDesign, 

WinterDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0
86

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

AHU-2_Fan_Sch WD, Sat 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0

SummerDesign, 

WinterDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

VAV_SAT_SCH All 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8

CAV_SAT_SCH All 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1 11.1

HW-Loop-Temp-Schedule All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

PlantOnSched All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

CW-Loop-Temp-Schedule All 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7

HeatSys1 Loop Setpoint 

Sched All 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2 82.2

BLDG_SWH_SCH WD, SummerDesign 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.17 0.58 0.66 0.78 0.82 0.71 0.82 0.78 0.74 0.63 0.41 0.18 0.18 0.18 0.1 0.01 0.01

Sat 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.2 0.28 0.3 0.3 0.24 0.24 0.23 0.23 0.23 0.1 0.01 0.01 0.01 0.01 0.01 0.01

Other 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01 0.01

Water Equipment Latent 

fract sched All 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

Water Equipment Sensible 

fract sched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

Water Equipment Hot Supply 

Temp Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

Water Equipment Temp 

Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

SWHSys1 Water Heater 

Ambient Temperature 

Schedule Name All 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22

SWHSys1 Water Heater 

Setpoint Temperature 

Schedule Name All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1-Loop-TempSchedule All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60
87

Table B-8 Primary School Hourly Operation Schedules 

Schedule

Through

(Date) Day 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON 12/31 All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

BLDG_EQUIP_SCH 6/30 WD, SummerDesign 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.35 0.35 0.35 0.35 0.35 0.35 0.35

Other 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35

9/1 WD, SummerDesign 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.25 0.25 0.25 0.25 0.25 0.25 0.25

Other 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25

12/31 WD, SummerDesign 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.35 0.35 0.35 0.35 0.35 0.35 0.35

Other 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35

BLDG_LIGHT_SCH 6/30 WD, SummerDesign 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.18 0.18 0.18

Other 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18

9/1 WD, SummerDesign 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.18 0.18 0.18 0.18

Other 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18

12/31 WD, SummerDesign 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.18 0.18 0.18

Other 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18

BLDG_OCC_SCH 6/30 WD, SummerDesign 0 0 0 0 0 0 0 0 0.75 0.75 0.75 0.75 0.75 0.75 0.75 0.75 0.15 0.15 0.15 0.15 0.15 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

9/1 WD, SummerDesign 0 0 0 0 0 0 0 0 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

12/31 WD, SummerDesign 0 0 0 0 0 0 0 0 0.75 0.75 0.75 0.75 0.75 0.75 0.75 0.75 0.15 0.15 0.15 0.15 0.15 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_OCC_SCH_Cafeteria 6/30 WD, SummerDesign 0 0 0 0 0 0 0 0.15 0.15 0.05 0.05 0.95 0.95 0.15 0.15 0 0 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

9/1 WD, SummerDesign 0 0 0 0 0 0 0 0 0 0.25 0.25 0.25 0.25 0.25 0.25 0 0 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

12/31 WD, SummerDesign 0 0 0 0 0 0 0 0.15 0.15 0.05 0.05 0.95 0.95 0.15 0.15 0 0 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_OCC_SCH_Gym 6/30 WD, SummerDesign 0 0 0 0 0 0 0 0 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.95 0.95 0.95 0.95 0.95 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

9/1 WD, SummerDesign 0 0 0 0 0 0 0 0 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

12/31 WD, SummerDesign 0 0 0 0 0 0 0 0 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.95 0.95 0.95 0.95 0.95 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_OCC_SCH_Offices 6/30 WD, SummerDesign 0 0 0 0 0 0 0 0 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.15 0.15 0.15 0.15 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

9/1 WD, SummerDesign 0 0 0 0 0 0 0 0 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

12/31 WD, SummerDesign 0 0 0 0 0 0 0 0 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.15 0.15 0.15 0.15 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

KITCHEN_ELEC_EQUIP_SCH 6/30 WD, SummerDesign 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.15 0.15 0.25 0.25 0.25 0.15 0.15 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

Other 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

9/1 WD, SummerDesign 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.13 0.13 0.2 0.2 0.2 0.13 0.13 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

Other 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

12/31 WD, SummerDesign 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.15 0.15 0.25 0.25 0.25 0.15 0.15 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1
88

Schedule

Through

(Date) Day 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

Other 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

KITCHEN_GAS_EQUIP_SCH 6/30 WD, SummerDesign 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.15 0.15 0.2 0.2 0.2 0.1 0.1 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02

Other 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02

9/1 WD, SummerDesign 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.1 0.1 0.15 0.15 0.15 0.1 0.1 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02

Other 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02

12/31 WD, SummerDesign 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.15 0.15 0.2 0.2 0.2 0.1 0.1 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02

Other 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02

Kitchen_Exhaust_SCH 12/31 WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

INFIL_SCH 12/31 All 1 1 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 1 1 1

WORK_EFF_SCH 12/31 All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

CLOTHING_SCH 04/30 All 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1

09/30 All 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6

12/31 All 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1

ACTIVITY_SCH 12/31 All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH 12/31 All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

CLGSETP_SCH 6/30 SummerDesign 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24

WE, Hol, 

WinterDesign 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27

Other 27 27 27 27 27 27 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 27 27 27

9/1 SummerDesign 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24

WE, Hol, 

WinterDesign 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27

Other 27 27 27 27 27 27 27 24 24 24 24 24 24 24 24 24 24 24 27 27 27 27 27 27

12/31 SummerDesign 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24

WE, Hol, 

WinterDesign 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27

Other 27 27 27 27 27 27 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 27 27 27

CLGSETP_SCH_BathCorrMechKitchen 12/31 SummerDesign 27 27 27 27 27 27 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 27 27 27

Other 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27

HTGSETP_SCH 6/30 WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

WE, Hol, 

SummerDesign 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16

Other 16 16 16 16 16 16 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 16 16 16

9/1 WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

WE, Hol, 

SummerDesign 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16

Other 16 16 16 16 16 16 16 21 21 21 21 21 21 21 21 21 21 21 16 16 16 16 16 16

12/31 WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

WE, Hol, 

SummerDesign 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16

Other 16 16 16 16 16 16 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 16 16 16

HTGSETP_SCH_BathCorrMechKitchen 12/31 WinterDesign 16 16 16 16 16 16 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 16 16 16

Other 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16

HVACOperationSchd 12/31 WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0
89

Schedule

Through

(Date) Day 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

MinOA_Sched 12/31 WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Seasonal-Reset-Supply-Air-Temp-Sch 12/31 All 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8

Dual Zone Control Type Sched 12/31 All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

HW-Loop-Temp-Schedule 12/31 All 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67

PlantOnSched 12/31 All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Kitchen_ZN_1_FLR_1_Case:1_WALKIN

FREEZER_CaseCreditReduxSched 12/31 All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.2 0.2 0.2

Kitchen_ZN_1_FLR_1_Case:1_WALKIN

FREEZER_CaseDefrost2aDaySched 12/31 All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Kitchen_ZN_1_FLR_1_Case:1_WALKIN

FREEZER_CaseDripDown2aDaySched 12/31 All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Kitchen_ZN_1_FLR_1_Case:1_WALKIN

FREEZER_WalkInStockingSched 12/31 Tue, Fri 0 0 0 0 725 417 290 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0 0 0 0 125 117 90 0 0 0 0 0 0 0 0 0 0 0 0 125 117 90 0 0

Kitchen_ZN_1_FLR_1_Case:2_SELFCO

NTAINEDDISPLAYCASE_CaseStocking

Sched 12/31 All 0 0 0 0 0 0 50 70 70 80 70 50 50 80 90 80 0 0 0 0 0 0 0 0

BLDG_SWH_SCH 6/30 WD, SummerDesign 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.34 0.6 0.63 0.72 0.79 0.83 0.61 0.65 0.1 0.1 0.19 0.25 0.22 0.22 0.12 0.09

Sat, WinterDesign 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.05 0.05 0.05 0.05 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03

Other 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.05 0.05 0.05 0.05 0.05 0.05 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03

9/1 WD, SummerDesign 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.19 0.25 0.22 0.22 0.12 0.09

Sat, WinterDesign 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.05 0.05 0.05 0.05 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03

Other 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.05 0.05 0.05 0.05 0.05 0.05 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03

12/31 WD, SummerDesign 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.34 0.6 0.63 0.72 0.79 0.83 0.61 0.65 0.1 0.1 0.19 0.25 0.22 0.22 0.12 0.09

Sat, WinterDesign 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.05 0.05 0.05 0.05 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03

Other 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.05 0.05 0.05 0.05 0.05 0.05 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03

SHW_default Latent fract sched 12/31 All 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

SHW_default Sensible fract sched 12/31 All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

SHW_Bath Hot Supply Temp Sched 12/31 All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

SHW_Bath Temp Sched 12/31 All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

SHW_Kitchen Hot Supply Temp Sched 12/31 All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49

SHW_Kitchen Temp Sched 12/31 All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49

SWHSys1 Water Heater Ambient 

Temperature Schedule Name 12/31 All 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22

SWHSys1 Water Heater Setpoint 

Temperature Schedule Name 12/31 All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1-Loop-Temp-Schedule 12/31 All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60
90

Table B-9 Retail Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

BLDG_EQUIP_SCH WD 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.7 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.8 0.8 0.7 0.4 0.2 0.2

Sat 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.3 0.5 0.8 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.5 0.5 0.3 0.15 0.15

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.3 0.3 0.6 0.6 0.8 0.8 0.8 0.8 0.8 0.6 0.4 0.15 0.15 0.15 0.15 0.15

BLDG_LIGHT_SCH WD 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.2 0.5 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.6 0.6 0.5 0.2 0.05 0.05

Sat 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.3 0.6 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.5 0.3 0.3 0.1 0.05 0.05

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.4 0.4 0.6 0.6 0.6 0.6 0.6 0.4 0.2 0.05 0.05 0.05 0.05 0.05

BLDG_OCC_SCH WD 0 0 0 0 0 0 0 0.1 0.2 0.5 0.5 0.7 0.7 0.7 0.7 0.8 0.7 0.5 0.5 0.3 0.3 0 0 0

SummerDesign, 

WinterDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Sat 0 0 0 0 0 0 0 0.1 0.2 0.5 0.6 0.8 0.8 0.8 0.8 0.8 0.8 0.6 0.2 0.2 0.2 0.1 0 0

Other 0 0 0 0 0 0 0 0 0 0.1 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.2 0.1 0 0 0 0 0

INFIL_HALF_ON_SCH WD, SummerDesign 1 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 1 1 1

Sat 1 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 1 1

WinterDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Other 1 1 1 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 1 1 1 1 1 1 1

INFIL_FRONT_SCH WD, SummerDesign 0.25 0.25 0.25 0.25 0.25 0.25 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0.25 0.25 0.25

Sat 0.25 0.25 0.25 0.25 0.25 0.25 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0.25 0.25

WinterDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Other 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 1 1 1 1 1 1 1 1 1 0.25 0.25 0.25 0.25 0.25 0.25 0.25

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

CLGSETP_SCH WD, SummerDesign 30 30 30 30 30 30 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 30 30 30

Sat 30 30 30 30 30 30 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 30 30

WinterDesign 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30

Sun, Hol, Other 30 30 30 30 30 30 30 30 24 24 24 24 24 24 24 24 24 24 24 30 30 30 30 30

Dual Zone Control Type Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

FRONT_ENTRY_COOLING All 90 90 90 90 90 90 90 90 90 90 90 90 90 90 90 90 90 90 90 90 90 90 90 90

HTGSETP_SCH WD 15.6 15.6 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 15.6 15.6 15.6

SummerDesign 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

Sat 15.6 15.6 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 15.6 15.6

Sun, Hol, Other 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 15.6 15.6 15.6 15.6 15.6

HVACOperationSchd WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0

Sat, WinterDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0

Other 0 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0
91

Table B-10 Secondary School Hourly Operation Schedules 

Schedule Through Day 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON 12/31 All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Kitchen_Exhaust_SCH 12/31 WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_ELEVATORS 12/31 WD, SummerDesign 0 0 0 0 0 0 0 0 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.15 0 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_EQUIP_SCH 6/30 WD, SummerDesign 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.35 0.35 0.35 0.35 0.35 0.35 0.35

Other 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35

9/1 WD, SummerDesign 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.25 0.25 0.25 0.25 0.25 0.25 0.25

Other 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25

12/31 WD, SummerDesign 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.35 0.35 0.35 0.35 0.35 0.35 0.35

Other 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35

BLDG_LIGHT_SCH 6/30 WD, SummerDesign 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.18 0.18 0.18

Other 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18

9/1 WD, SummerDesign 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.18 0.18 0.18 0.18

Other 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18

12/31 WD, SummerDesign 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.18 0.18 0.18

Other 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18 0.18

BLDG_OCC_SCH 6/30 WD, SummerDesign 0 0 0 0 0 0 0 0 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.15 0.15 0.15 0.15 0.15 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

9/1 WD, SummerDesign 0 0 0 0 0 0 0 0 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

12/31 WD, SummerDesign 0 0 0 0 0 0 0 0 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.15 0.15 0.15 0.15 0.15 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_OCC_SCH_Auditorium 6/30 WD, SummerDesign 0 0 0 0 0 0 0 0 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.95 0.95 0.1 0.1 0.1 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

9/1 WD, SummerDesign 0 0 0 0 0 0 0 0 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.35 0.35 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

12/31 WD, SummerDesign 0 0 0 0 0 0 0 0 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.95 0.95 0.1 0.1 0.1 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_OCC_SCH_Cafeteria 6/30 WD, SummerDesign 0 0 0 0 0 0 0 0.15 0.15 0.05 0.05 0.95 0.95 0.15 0.15 0 0 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

9/1 WD, SummerDesign 0 0 0 0 0 0 0 0 0 0.25 0.25 0.25 0.25 0.25 0.25 0 0 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

12/31 WD, SummerDesign 0 0 0 0 0 0 0 0.15 0.15 0.05 0.05 0.95 0.95 0.15 0.15 0 0 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_OCC_SCH_Extend 6/30 WD, SummerDesign 0 0 0 0 0 0 0 0 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

9/1 WD, SummerDesign 0 0 0 0 0 0 0 0 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

12/31 WD, SummerDesign 0 0 0 0 0 0 0 0 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_OCC_SCH_Gym 6/30 WD, SummerDesign 0 0 0 0 0 0 0 0 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.95 0.95 0.95 0.95 0.95 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0
92

Schedule Through Day 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

9/1 WD, SummerDesign 0 0 0 0 0 0 0 0 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

12/31 WD, SummerDesign 0 0 0 0 0 0 0 0 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.95 0.95 0.95 0.95 0.95 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_OCC_SCH_Offices 6/30 WD, SummerDesign 0 0 0 0 0 0 0 0 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.15 0.15 0.15 0.15 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

9/1 WD, SummerDesign 0 0 0 0 0 0 0 0 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

12/31 WD, SummerDesign 0 0 0 0 0 0 0 0 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.95 0.15 0.15 0.15 0.15 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

KITCHEN_ELEC_EQUIP_SCH 6/30 WD, SummerDesign 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.15 0.15 0.25 0.25 0.25 0.15 0.15 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

Other 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

9/1 WD, SummerDesign 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.13 0.13 0.2 0.2 0.2 0.13 0.13 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

Other 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

12/31 WD, SummerDesign 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.15 0.15 0.25 0.25 0.25 0.15 0.15 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

Other 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

KITCHEN_GAS_EQUIP_SCH 6/30 WD, SummerDesign 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.15 0.15 0.2 0.2 0.2 0.1 0.1 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02

Other 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02

9/1 WD, SummerDesign 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.1 0.1 0.15 0.15 0.15 0.1 0.1 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02

WE, WinterDesign, Hol, Other 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02

12/31 WD, SummerDesign 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.15 0.15 0.2 0.2 0.2 0.1 0.1 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02

WE, WinterDesign, Hol, Other 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02 0.02

INFIL_SCH 12/31 All 1 1 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 1 1 1

ACTIVITY_SCH 12/31 All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH 12/31 All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

CLOTHING_SCH 04/30 All 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1

09/30 All 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6

12/31 All 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1 1.1

WORK_EFF_SCH 12/31 All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

CLGSETP_SCH 6/30 SummerDesign 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24

WE, Hol, WinterDesign 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27

Other 27 27 27 27 27 27 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 27 27 27

9/1 SummerDesign 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24

WE, Hol, WinterDesign 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27

Other 27 27 27 27 27 27 27 24 24 24 24 24 24 24 24 24 24 24 27 27 27 27 27 27

12/31 SummerDesign 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24

WE, Hol, WinterDesign 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27

Other 27 27 27 27 27 27 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 27 27 27

CLGSETP_SCH_BathCorrMechKitchen 12/31 SummerDesign 27 27 27 27 27 27 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 27 27 27

Other 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27 27

HTGSETP_SCH 6/30 WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

WE, Hol, SummerDesign 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16

Other 16 16 16 16 16 16 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 16 16 16

9/1 WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

WE, Hol, SummerDesign 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16

Other 16 16 16 16 16 16 16 21 21 21 21 21 21 21 21 21 21 21 16 16 16 16 16 16
93

Schedule Through Day 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

12/31 WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

WE, Hol, SummerDesign 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16

Other 16 16 16 16 16 16 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 16 16 16

HTGSETP_SCH_BathCorrMechKitchen 12/31 WinterDesign 16 16 16 16 16 16 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 16 16 16

Other 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16 16

HVACOperationSchd 12/31 WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

MinOA_Sched 12/31 WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Seasonal-Reset-Supply-Air-Temp-Sch 12/31 All 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8 12.8

Dual Zone Control Type Sched 12/31 All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

CW-Loop-Temp-Schedule 12/31 All 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7 6.7

HW-Loop-Temp-Schedule 12/31 All 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67 67

PlantOnSched 12/31 All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Kitchen_ZN_1_FLR_1_Case:1_WALKINFR

EEZER_CaseCreditReduxSched 12/31 All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.2 0.2 0.2

Kitchen_ZN_1_FLR_1_Case:1_WALKINFR

EEZER_CaseDefrost2aDaySched 12/31 All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Kitchen_ZN_1_FLR_1_Case:1_WALKINFR

EEZER_CaseDripDown2aDaySched 12/31 All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Kitchen_ZN_1_FLR_1_Case:1_WALKINFR

EEZER_WalkInStockingSched 12/31 Tue, Fri 0 0 0 0 725 417 290 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0 0 0 0 125 117 90 0 0 0 0 0 0 0 0 0 0 0 0 125 117 90 0 0

Kitchen_ZN_1_FLR_1_Case:2_SELFCONT

AINEDDISPLAYCASE_CaseStockingSched 12/31 All 0 0 0 0 0 0 50 70 70 80 70 50 50 80 90 80 0 0 0 0 0 0 0 0

BLDG_SWH_SCH 6/15 WD, SummerDesign 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.34 0.6 0.63 0.72 0.79 0.83 0.61 0.65 0.1 0.1 0.19 0.25 0.22 0.22 0.12 0.09

Sat, WinterDesign 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.05 0.05 0.05 0.05 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03

Sun, Hol, Other 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.05 0.05 0.05 0.05 0.05 0.05 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03

9/15 WD, SummerDesign 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.19 0.25 0.22 0.22 0.12 0.09

Sat, WinterDesign 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.05 0.05 0.05 0.05 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03

Sun, Hol, Other 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.05 0.05 0.05 0.05 0.05 0.05 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03

12/31 WD, SummerDesign 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.34 0.6 0.63 0.72 0.79 0.83 0.61 0.65 0.1 0.1 0.19 0.25 0.22 0.22 0.12 0.09

Sat, WinterDesign 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.05 0.05 0.05 0.05 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03

Sun, Hol, Other 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.05 0.05 0.05 0.05 0.05 0.05 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03 0.03

Showers_SWH_SCH 6/30 WD, SummerDesign 0 0 0 0 0 0 0 0.6 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 1 1 1 0 0 0 0 0

WE 0 0 0 0 0 0 0 0 0 0 0.4 0.14 0.14 0.14 0.14 0.14 0 0 0 0 0 0.8 0 0

WinterDesign, Hol, Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

9/1 WD, SummerDesign 0 0 0 0 0 0 0 0 0.3 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0 0 0 0 0 0 0 0

WE, WinterDesign, Hol, Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

12/31 WD, SummerDesign 0 0 0 0 0 0 0 0.6 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 1 1 1 0 0 0 0 0

WE 0 0 0 0 0 0 0 0 0 0 0.4 0.14 0.14 0.14 0.14 0.14 0 0 0 0 0 0.8 0 0

WinterDesign, Hol, Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Latent fract sched 12/31 All 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

Sensible fract sched 12/31 All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

Hot Supply Temp Sched 12/31 All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

SHW_default Temp Sched 12/31 All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

Kitchen Hot Supply Temp Sched 12/31 All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49
94

Schedule Through Day 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

SHW_Kitchen Temp Sched 12/31 All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49

SWHSys1 Water Heater Ambient 

Temperature Schedule Name 12/31 All 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22

SWHSys1 Water Heater Setpoint 

Temperature Schedule Name 12/31 All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1-Loop-Temp-Schedule 12/31 All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60
95

Table B-11 Full Service Restaurant Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

BLDG_EQUIP_SCH Weekday 0.1 0.1 0.1 0.1 0.1 0.1 0.25 0.35 0.35 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.25 0.25

Sat 0.1 0.1 0.1 0.1 0.1 0.1 0.25 0.35 0.35 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.25 0.25

SummerDesign 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.1 0.1 0.1 0.1 0.1 0.1 0.25 0.35 0.35 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.35 0.35 0.35 0.25 0.25 0.25 0.25 0.25

BLDG_LIGHT_SCH SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Weekday, Sat, 

Sun, Hol, Other 0.45 0.15 0.15 0.15 0.15 0.45 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9

BLDG_OCC_SCH WD 0.05 0 0 0 0 0.05 0.1 0.4 0.4 0.4 0.2 0.5 0.8 0.7 0.4 0.2 0.25 0.5 0.8 0.8 0.8 0.5 0.35 0.2

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sat 0.05 0 0 0 0 0 0.05 0.5 0.5 0.4 0.2 0.45 0.5 0.5 0.35 0.3 0.3 0.3 0.7 0.9 0.7 0.65 0.55 0.35

Sun, Hol, Other 0.05 0 0 0 0 0 0.05 0.5 0.5 0.2 0.2 0.3 0.5 0.5 0.3 0.2 0.25 0.35 0.55 0.65 0.7 0.35 0.2 0.2

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

GAS_EQUIP_SCH WD, Sat 0.02 0.02 0.02 0.02 0.02 0.05 0.1 0.15 0.2 0.15 0.25 0.25 0.25 0.2 0.15 0.2 0.3 0.3 0.3 0.2 0.2 0.15 0.1 0.05

SummerDesign 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.02 0.02 0.02 0.02 0.02 0.05 0.1 0.15 0.2 0.15 0.25 0.25 0.25 0.2 0.15 0.2 0.3 0.3 0.3 0.2 0.2 0.15 0.1 0.05

Kitchen_Exhaust_SCH All 1 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

INFIL_HALF_ON_SCH

WD, 

SummerDesign 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

Sat, WinterDesign 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

Sun, Hol, Other 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Dual Zone Control Type Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

CLGSETP_KITCHEN_SCH WinterDesign 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30

Other 26 30 30 30 30 26 26 26 26 26 26 26 26 26 26 26 26 26 26 26 26 26 26 26

HTGSETP_KITCHEN_SCH SummerDesign 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

WinterDesign 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19

Other 19 15.6 15.6 15.6 15.6 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19 19

CLGSETP_SCH WinterDesign 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30

Other 24 30 30 30 30 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24

HTGSETP_SCH SummerDesign 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

Other 21 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

HVACOperationSchd All 1 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

MinOA_Sched All 1 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1
96

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

Kitchen_Case:1_WALKINFREEZER_

CaseCreditReduxSched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.2 0.2 0.2

Kitchen_Case:1_WALKINFREEZER_

CaseDefrost2aDaySched All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Kitchen_Case:1_WALKINFREEZER_

CaseDripDown2aDaySched All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Kitchen_Case:1_WALKINFREEZER_

WalkInStockingSched Tue, Fri 0 0 0 0 725 417 290 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0 0 0 0 125 117 90 0 0 0 0 0 0 0 0 0 0 0 0 125 117 90 0 0

Kitchen_Case:2_SELFCONTAINEDDI

SPLAYCASE_CaseStockingSched All 0 0 0 0 0 0 50 70 70 80 70 50 50 80 90 80 0 0 0 0 0 0 0 0

BLDG_SWH_SCH

WD, 

SummerDesign 0.2 0 0 0 0 0 0.15 0.6 0.55 0.45 0.4 0.45 0.4 0.35 0.3 0.3 0.3 0.4 0.55 0.6 0.5 0.55 0.45 0.25

Sat, WinterDesign 0.2 0 0 0 0 0 0.15 0.15 0.15 0.5 0.45 0.5 0.5 0.45 0.4 0.4 0.35 0.4 0.55 0.55 0.5 0.55 0.4 0.3

Sun, Hol, Other 0.25 0 0 0 0 0 0.15 0.15 0.15 0.15 0.5 0.5 0.4 0.4 0.3 0.3 0.3 0.4 0.5 0.5 0.4 0.5 0.4 0.2

Kitchen Water Equipment Hot Supply 

Temp Sched All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49

Kitchen Water Equipment Latent fract 

sched All 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

Kitchen Water Equipment Sensible 

fract sched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

Kitchen Water Equipment Temp 

Sched All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49

PlantOnSched All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

SWHSys1 Water Heater Ambient 

Temperature Schedule Name All 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22

SWHSys1 Water Heater Setpoint

Temperature Schedule Name All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1-Loop-Temp-Schedule All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60
97

Table B-12 Small Hotel Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

BLDG_ELEVATORS All 0.05 0.05 0.05 0.05 0.1 0.2 0.4 0.5 0.5 0.35 0.15 0.15 0.15 0.15 0.15 0.15 0.35 0.5 0.5 0.4 0.4 0.3 0.2 0.1

BLDG_EQUIP_SCH WD 0.3 0.25 0.2 0.2 0.2 0.3 0.5 0.6 0.5 0.5 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.7 0.9 0.95 0.9 0.7 0.4

Sat 0.3 0.3 0.2 0.2 0.2 0.2 0.4 0.4 0.5 0.5 0.4 0.35 0.35 0.35 0.35 0.35 0.35 0.35 0.7 0.8 0.8 0.8 0.7 0.4

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.4 0.4 0.3 0.3 0.3 0.3 0.4 0.5 0.5 0.4 0.4 0.4 0.4 0.3 0.3 0.3 0.3 0.3 0.6 0.8 0.9 0.7 0.6 0.4

BLDG_LIGHT_SCH WD 0.2 0.15 0.1 0.1 0.1 0.2 0.4 0.5 0.4 0.4 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.6 0.8 0.9 0.8 0.6 0.3

Sat 0.2 0.2 0.1 0.1 0.1 0.1 0.3 0.3 0.4 0.4 0.3 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.6 0.7 0.7 0.7 0.6 0.3

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.3 0.3 0.2 0.2 0.2 0.2 0.3 0.4 0.4 0.3 0.3 0.3 0.3 0.2 0.2 0.2 0.2 0.2 0.5 0.7 0.8 0.6 0.5 0.3

BLDG_OCC_SCH WD 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.4 0.4 0.2 0.2 0.2 0.2 0.2 0.2 0.3 0.5 0.5 0.5 0.7 0.7 0.8 0.9 0.9

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Sat 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.5 0.5 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.5 0.6 0.6 0.6 0.7 0.7 0.7

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.5 0.5 0.5 0.3 0.3 0.2 0.2 0.2 0.3 0.4 0.4 0.6 0.6 0.8 0.8 0.8

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Corridor_Ltg_Sch All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

EmployeeLounge_Eqp_Sch WD 0.11 0.11 0.11 0.11 0.11 0.19 0.19 0.25 1 1 0.86 0.86 1 0.86 0.86 0.86 0.86 0.86 0.25 0.19 0.11 0.11 0.11 0.11

Sat, Sun, Hol 0.11 0.11 0.11 0.11 0.11 0.19 0.19 0.25 1 1 0.86 0.86 1 0.86 0.86 0.86 0.86 0.86 0.25 0.19 0.11 0.11 0.11 0.11

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

EmployeeLounge_Ltg_Sch WD 0.05 0.05 0.05 0.05 0.05 0.15 0.4 0.5 1 1 1 1 1 1 1 1 1 1 0.5 0.4 0.15 0.15 0.05 0.05

Sat, Sun, Hol 0.05 0.05 0.05 0.05 0.05 0.15 0.3 0.4 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.4 0.3 0.15 0.15 0.05 0.05

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

EmployeeLounge_Occ_Sch WD 0 0 0 0 0 0.1 0.1 0.2 0.2 0.2 0.2 0.2 0.7 0.2 0.2 0.2 0.2 0.2 0.1 0.1 0 0 0 0

Sat, Sun, Hol 0 0 0 0 0 0.05 0.05 0.05 0.1 0.1 0.1 0.1 0.2 0.1 0.1 0.1 0.1 0.1 0.05 0.05 0 0 0 0

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

ExerciseRoom_Eqp_Sch All 0 0 0 0 0 0 0.5 1 1 0.5 0.5 0.5 0 0.5 0.5 0.5 1 0.5 0.5 1 1 0.5 0.5 0

ExerciseRoom_Ltg_Sch_Base All 0 0 0 0 0 0 0.5 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0.5 0

ExerciseRoom_Occ_Sch All 0 0 0 0 0 0 0.5 1 1 1 1 0.5 0 1 1 1 1 1 1 1 1 1 0.5 0
98

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

GuestRoom_Eqp_Sch WD 0.2 0.2 0.2 0.2 0.2 0.2 0.62 0.9 0.43 0.43 0.26 0.26 0.26 0.26 0.26 0.26 0.26 0.51 0.51 0.49 0.66 0.7 0.35 0.2

Sat, Sun, Hol 0.2 0.2 0.2 0.2 0.2 0.2 0.3 0.62 0.9 0.62 0.29 0.29 0.29 0.29 0.29 0.29 0.29 0.43 0.51 0.49 0.66 0.7 0.35 0.2

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

GuestRoom_Ltg_Sch_Base WD 0.22 0.17 0.11 0.11 0.11 0.22 0.44 0.56 0.44 0.44 0.28 0.28 0.28 0.28 0.28 0.28 0.28 0.28 0.67 0.89 1 0.89 0.67 0.33

Sat, Sun, Hol 0.26 0.26 0.11 0.11 0.11 0.11 0.41 0.41 0.56 0.56 0.41 0.33 0.33 0.33 0.33 0.33 0.33 0.33 0.85 1 1 1 0.85 0.41

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

GuestRoom_Occ_Sch WD 0.65 0.65 0.65 0.65 0.65 0.65 0.5 0.28 0.28 0.13 0.13 0.13 0.13 0.13 0.13 0.2 0.35 0.35 0.35 0.5 0.5 0.58 0.65 0.65

Sat, Sun, Hol 0.65 0.65 0.65 0.65 0.65 0.65 0.5 0.34 0.34 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.34 0.35 0.65 0.65 0.5 0.5 0.5

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

INFIL_HALF_ON_SCH All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

INFIL_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

LaundryRoom_Eqp_Elec_Sch WD, Sat, Sun, Hol 0 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0 0

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

LaundryRoom_Eqp_Gas_Sch WD, Sat, Sun, Hol 0 0 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

LaundryRoom_Ltg_Sch All 0 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0

LaundryRoom_Occ_Sch WD 0 0 0 0 0 0 0 0 0.09 0.09 0.18 0.18 0 0.18 0.18 0.18 0.09 0 0 0 0 0 0 0

Sat, Sun, Hol 0 0 0 0 0 0 0 0 0.09 0.09 0.18 0.18 0 0.18 0.18 0.18 0.09 0 0 0 0 0 0 0

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

MeetingRoom_Eqp_Sch All 0 0 0 0 0 0 0 0.05 0.54 0.54 0.26 0.26 0.05 0.54 0.54 0.26 0.26 0.26 0.05 0.05 0 0 0 0

MeetingRoom_Ltg_Sch_Base WD, Sat, Sun, Hol 0 0 0 0 0 0.2 0.3 0.5 1 1 1 1 1 1 1 1 1 1 0.5 0.3 0.2 0.05 0 0

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

MeetingRoom_Occ_Sch WD 0 0 0 0 0 0 0 0.05 0.5 0.5 0.2 0.2 0.05 0.5 0.5 0.2 0.2 0.2 0.05 0.05 0 0 0 0

Sat, Sun, Hol 0 0 0 0 0 0 0 0.05 0.5 0.5 0.2 0.2 0.05 0.5 0.5 0.2 0.2 0.2 0.05 0.05 0 0 0 0

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Office_Eqp_Sch WD 0.33 0.33 0.33 0.33 0.33 0.38 0.38 0.43 0.43 0.43 1 1 0.94 1 1 1 1 0.75 0.63 0.63 0.48 0.48 0.33 0.33
99

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

Sat, Sun, Hol 0.33 0.33 0.33 0.33 0.33 0.38 0.38 0.43 0.63 0.63 0.63 0.63 0.63 0.63 0.63 0.63 0.63 0.63 0.48 0.48 0.48 0.48 0.33 0.33

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Office_Ltg_Sch_Base WD, Sat, Sun, Hol 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.61 0.9 0.9 0.9 0.9 0.8 0.9 0.9 0.9 0.9 0.61 0.5 0.5 0.5 0.5 0.5 0.5

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Office_Occ_Sch WD 0.2 0.2 0.2 0.2 0.2 0.2 0.3 0.4 1 1 1 1 0.5 1 1 1 1 0.4 0.3 0.2 0.2 0.2 0.2 0.2

Sat, Sun, Hol 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.3 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.3 0.2 0.2 0.2 0.2 0.2 0.2

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Storage_Ltg_Sch WD 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.2 0.2 0.2 0.2 0.1 0.1

Sat, Sun, Hol 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.2 0.2 0.2 0.2 0.1 0.1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

SummerDesign, 

CustomDay1, 

CustomDay2 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

ALWAYS_OFF All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

CLGSETP_SCH All 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24

Dual Zone Control Type Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

HTGSETP_SCH All 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

HVACOperationSchd All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

MinOA_Sched All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

UnitHeater_ClgSP_Sch All 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40 40

UnitHeater_HtgSP_Sch All 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

GuestRoom_SWH_Sch WD 0.2 0.15 0.15 0.15 0.2 0.35 0.6 0.8 0.55 0.4 0.3 0.2 0.2 0.2 0.2 0.2 0.2 0.3 0.55 0.4 0.4 0.6 0.45 0.25

Other 0.2 0.15 0.15 0.15 0.2 0.25 0.35 0.6 0.8 0.55 0.4 0.3 0.2 0.2 0.2 0.2 0.2 0.25 0.3 0.4 0.4 0.4 0.6 0.35

LaundryRoom_SWH_Sch All 0 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0 0

Water Equipment Latent fract sched All 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

Water Equipment Sensible fract sched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

Water Equipment Hot Supply Temp 

Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

Water Equipment Temp Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

Laundry Water Equipment Hot Supply 

Temp Sched All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

Laundry Water Equipment Temp 

Sched All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1 Water Heater Ambient 

Temperature Schedule Name All 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22

SWHSys1 Water Heater Setpoint 

Temperature Schedule Name All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1-Loop-Temp-Schedule All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60
100

Table B-13 Small Office Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

INFIL_QUARTER_ON_SCH WD, SummerDesign 1 1 1 1 1 1 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 1 1

Sat, WinterDesign 1 1 1 1 1 1 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 0.25 1 1 1 1 1 1

Sun, Hol, Other 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

BLDG_OCC_SCH SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0.05 0.05

WD 0 0 0 0 0 0 0.1 0.2 0.95 0.95 0.95 0.95 0.5 0.95 0.95 0.95 0.95 0.3 0.1 0.1 0.05 0.05 0.05 0.05

Sat 0 0 0 0 0 0 0.1 0.1 0.3 0.3 0.3 0.3 0.1 0.1 0.1 0.1 0.1 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_LIGHT_SCH WD 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.3 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.5 0.3 0.3 0.2 0.2 0.1 0.05

Sat 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.3 0.3 0.3 0.3 0.15 0.15 0.15 0.15 0.15 0.05 0.05 0.05 0.05 0.05 0.05 0.05

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

BLDG_EQUIP_SCH WD 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.9 0.9 0.9 0.9 0.8 0.9 0.9 0.9 0.9 0.5 0.4 0.4 0.4 0.4 0.4 0.4

Sat 0.3 0.3 0.3 0.3 0.3 0.3 0.4 0.4 0.5 0.5 0.5 0.5 0.35 0.35 0.35 0.35 0.35 0.3 0.3 0.3 0.3 0.3 0.3 0.3

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Other 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3 0.3

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

CLGSETP_SCH WD, SummerDesign 26.7 26.7 26.7 26.7 26.7 26.7 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 26.7 26.7

Sat 26.7 26.7 26.7 26.7 26.7 26.7 24 24 24 24 24 24 24 24 24 24 24 24 26.7 26.7 26.7 26.7 26.7 26.7

Other 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7

HTGSETP_SCH WD 15.6 15.6 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 15.6 15.6

Sat 15.6 15.6 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 21 15.6 15.6 15.6 15.6 15.6 15.6

WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

Other 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

MinOA_Sched WD, SummerDesign 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0

Sat, WinterDesign 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Dual Zone Control Type Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

HVACOperationSchd WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0

Sat, WinterDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

BLDG_SWH_SCH WD, SummerDesign 0.05 0.05 0.05 0.05 0.05 0.08 0.07 0.19 0.35 0.38 0.39 0.47 0.57 0.54 0.34 0.33 0.44 0.26 0.21 0.15 0.17 0.08 0.05 0.05

Sat, WinterDesign 0.05 0.05 0.05 0.05 0.05 0.08 0.07 0.11 0.15 0.21 0.19 0.23 0.2 0.19 0.15 0.13 0.14 0.07 0.07 0.07 0.07 0.09 0.05 0.05

Other 0.04 0.04 0.04 0.04 0.04 0.07 0.04 0.04 0.04 0.04 0.04 0.06 0.06 0.09 0.06 0.04 0.04 0.04 0.04 0.04 0.04 0.07 0.04 0.04

Water Equipment Latent fract 

sched All 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05
101

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

Water Equipment Sensible fract 

sched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

SWHSys1 Water Heater Ambient 

Temperature Schedule Name All 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22

Water Equipment Temp Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

Water Equipment Hot Supply 

Temp Sched All 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3 43.3

SWHSys1 Water Heater Setpoint 

Temperature Schedule Name All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1-Loop-Temp-Schedule All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60
102

Table B-14 Strip Mall Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

BLDG_EQUIP_SCH WD 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.7 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.8 0.8 0.7 0.4 0.2 0.2

Sat 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.3 0.5 0.8 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.5 0.5 0.3 0.15 0.15

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.15 0.3 0.3 0.6 0.6 0.8 0.8 0.8 0.8 0.8 0.6 0.4 0.15 0.15 0.15 0.15 0.15

BLDG_LIGHT_SCH WD 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.2 0.5 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.6 0.6 0.5 0.2 0.05 0.05

Sat 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.3 0.6 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.5 0.3 0.3 0.1 0.05 0.05

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.4 0.4 0.6 0.6 0.6 0.6 0.6 0.4 0.2 0.05 0.05 0.05 0.05 0.05

BLDG_OCC_SCH WD 0 0 0 0 0 0 0 0.1 0.2 0.5 0.5 0.7 0.7 0.7 0.7 0.8 0.7 0.5 0.5 0.3 0.3 0 0 0

SummerDesign, 

WinterDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Sat 0 0 0 0 0 0 0 0.1 0.2 0.5 0.6 0.8 0.8 0.8 0.8 0.8 0.8 0.6 0.2 0.2 0.2 0.1 0 0

Other 0 0 0 0 0 0 0 0 0 0.1 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.2 0.1 0 0 0 0 0

INFIL_HALF_ON_SCH WD, SummerDesign 1 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 1 1 1

Sat 1 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 1 1

WinterDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Sun, Hol, Other 1 1 1 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 1 1 1 1 1 1 1

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

CLGSETP_SCH WD, SummerDesign 30 30 30 30 30 30 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 30 30 30

Sat 30 30 30 30 30 30 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 30 30

WinterDesign 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30

Sun, Hol, Other 30 30 30 30 30 30 30 30 24 24 24 24 24 24 24 24 24 24 24 30 30 30 30 30

Dual Zone Control Type Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

HTGSETP_SCH WD 15.6 15.6 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 15.6 15.6 15.6

SummerDesign 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

Sat 15.6 15.6 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 15.6 15.6

Other 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 15.6 15.6 15.6 15.6 15.6

HVACOperationSchd WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0

Sat, WinterDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0

Other 0 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0

MinOA_Sched WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0 0

Sat, WinterDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0

Other 0 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0
103

Table B-15 Supermarket Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Deli_Exhaust_SCH

WinterDesign, 

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Other 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0

BLDG_EQUIP_SCH WD 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.4 0.7 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.8 0.8 0.7 0.4 0.2 0.2

Sat 0.15 0.15 0.15 0.15 0.15 0.15 0.3 0.3 0.5 0.8 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.7 0.5 0.5 0.3 0.15 0.15

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.15 0.15 0.15 0.15 0.15 0.15 0.3 0.3 0.3 0.3 0.6 0.6 0.8 0.8 0.8 0.8 0.8 0.6 0.4 0.4 0.4 0.4 0.15 0.15

BLDG_LIGHT_SCH WD 0.05 0.05 0.05 0.05 0.05 0.05 0.2 0.2 0.5 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.6 0.6 0.5 0.2 0.05 0.05

Sat 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.3 0.6 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 0.5 0.3 0.3 0.1 0.05 0.05

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.05 0.05 0.05 0.05 0.05 0.05 0.1 0.1 0.1 0.1 0.4 0.4 0.6 0.6 0.6 0.6 0.6 0.4 0.2 0.2 0.2 0.2 0.05 0.05

BLDG_OCC_SCH WD 0 0 0 0 0 0 0.1 0.1 0.2 0.5 0.5 0.7 0.7 0.7 0.7 0.8 0.7 0.5 0.5 0.3 0.3 0.3 0 0

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Sat 0 0 0 0 0 0 0.1 0.1 0.2 0.5 0.6 0.8 0.8 0.8 0.8 0.8 0.8 0.6 0.2 0.2 0.2 0.1 0 0

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0 0 0 0 0 0 0.1 0.1 0.1 0.1 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.2 0.1 0.1 0.1 0.1 0 0

INFIL_HALF_ON_SCH WD, SummerDesign 1 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 1 1

Sat 1 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 1 1

WinterDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Sun, Hol, Other 1 1 1 1 1 1 1 1 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 1 1 1 1 1 1 1

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

CLGSETP_SCH WinterDesign 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30

Other 30 30 30 30 30 30 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 24 30 30

HTGSETP_SCH SummerDesign 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

Other 15.6 15.6 15.6 15.6 15.6 15.6 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 15.6 15.6

HVACOperationSchd All 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0

MinOA_Sched All 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 0 0

Dual Zone Control Type Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

Bakery_Case:1_WALKINFREEZER

_CaseCreditReduxSched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.2 0.2 0.2

Bakery_Case:1_WALKINFREEZER

_CaseDefrost2aDaySched All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Bakery_Case:1_WALKINFREEZER

_CaseDripDown2aDaySched All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Bakery_Case:1_WALKINFREEZER

_WalkInStockingSched Tue, Fri 0 0 0 0 725 417 290 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0
104

Schedule Day of Week123456789 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

Other0000 125 117 90000000000000 125 117 9000

Deli_Case:1_ 

MULTIDECKDIARYANDDELICASE

_CaseCreditReduxSched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.2 0.2 0.2

Deli_Case:1_ 

MULTIDECKDIARYANDDELICASE

_CaseDefrost2aDaySched All000000000000000000000000

Deli_Case:1_ 

MULTIDECKDIARYANDDELICASE

_CaseDripDown2aDaySched All000000000000000000000000

Deli_Case:1_ 

MULTIDECKDIARYANDDELICASE

_CaseStockingSched All

0000000000000 50 35000000000

Deli_Case:2_WALKINFREEZER_C

aseCreditReduxSched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.2 0.2 0.2

Deli_Case:2_WALKINFREEZER_C

aseDefrost2aDaySched All

000000000000000000000000

Deli_Case:2_WALKINFREEZER_C

aseDripDown2aDaySched All000000000000000000000000

Deli_Case:2_WALKINFREEZER_W

alkInStockingSched Tue, Fri

0000 725 417 29000000000000000000

Other0000 125 117 90000000000000 125 117 9000

Produce_Case:1_ 

MULTIDECKDIARYANDDELICASE_

CaseCreditReduxSched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.2 0.2 0.2

Produce_Case:1_ 

MULTIDECKDIARYANDDELICASE_

CaseDefrost2aDaySched All000000000000000000000000

Produce_Case:1_ 

MULTIDECKDIARYANDDELICASE_

CaseDripDown2aDaySched All

000000000000000000000000

Produce_Case:1_ 

MULTIDECKDIARYANDDELICASE_

CaseStockingSched All0000000000000 50 35000000000

Sales_Case:1_MEATDISPLAYCASE

_CaseDefrost2aDaySched All000000000000000000000000

Sales_Case:1_MEATDISPLAYCASE

_CaseDripDown2aDaySched All000000000000000000000000

Sales_Case:1_MEATDISPLAYCASE

_CaseStockingSched All0000000000000 50 35000000000

Sales_Case:2_ 

MULTIDECKDIARYANDDELICASE_

CaseCreditReduxSched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.2 0.2 0.2

Sales_Case:2_ 

MULTIDECKDIARYANDDELICASE_

CaseDefrost2aDaySched All000000000000000000000000

Sales_Case:2_ 

MULTIDECKDIARYANDDELICASE_

CaseDripDown2aDaySched All

000000000000000000000000
105

Schedule Day of Week123456789 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

Sales_Case:2_ 

MULTIDECKDIARYANDDELICASE_

CaseStockingSched All

0000000000000 50 35000000000

Sales_Case:3_GLASSDOORFROZE

NFOOD_CaseCreditReduxSched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.2 0.2 0.2

Sales_Case:3_GLASSDOORFROZE

NFOOD_CaseDefrost2aDaySched All000000000000000000000000

Sales_Case:3_GLASSDOORFROZE

NFOOD_CaseDripDown2aDaySched All

000000000000000000000000

Sales_Case:3_GLASSDOORFROZE

NFOOD_CaseStockingSched All0000000000000 50 35000000000

Sales_Case:4_OPENWELLICECRE

AMDISPLAYCASE_CaseCreditRedu

xSched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.6 0.2 0.2 0.2

Sales_Case:4_OPENWELLICECRE

AMDISPLAYCASE_CaseDefrost2aD

aySched All

000000000000000000000000

Sales_Case:4_OPENWELLICECRE

AMDISPLAYCASE_CaseDripDown2

aDaySched All000000000000000000000000

Sales_Case:4_OPENWELLICECRE

AMDISPLAYCASE_CaseStockingSc

hed All

0000000000000 50 35000000000

Sales_Case:5_WALKINFREEZER_C

aseCreditReduxSched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.2 0.2 0.2

Sales_Case:5_WALKINFREEZER_C

aseDefrost2aDaySched All000000000000000000000000

Sales_Case:5_WALKINFREEZER_C

aseDripDown2aDaySched All000000000000000000000000

Sales_Case:5_WALKINFREEZER_

WalkInStockingSched Tue, Fri

0000 725 417 29000000000000000000

Other0000 125 117 90000000000000 125 117 9000

Sales_Case:6_WALKINFREEZER_C

aseCreditReduxSched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.4 0.2 0.2 0.2

Sales_Case:6_WALKINFREEZER_C

aseDefrost2aDaySched All000000000000000000000000

Sales_Case:6_WALKINFREEZER_C

aseDripDown2aDaySched All

000000000000000000000000

Sales_Case:6_WALKINFREEZER_

WalkInStockingSched Tue, Fri0000 725 417 29000000000000000000

Other0000 125 117 90000000000000 125 117 9000

Sales_Case:7_WALKINFREEZER_C

aseCreditReduxSched All000000000000000000000000

Sales_Case:7_WALKINFREEZER_C

aseDefrost2aDaySched All000000000000000000000000

Sales_Case:7_WALKINFREEZER_C

aseDripDown2aDaySched All

000000000000000000000000

Sales_Case:7_WALKINFREEZER_

WalkInStockingSched Tue, Fri0000 725 417 29000000000000000000

Other0000 125 117 90000000000000 125 117 9000

BLDG_SWH_SCH WD, SummerDesign 0.04 0.05 0.05 0.04 0.04 0.04 0.04 0.15 0.23 0.32 0.41 0.57 0.62 0.61 0.5 0.45 0.46 0.47 0.42 0.34 0.33 0.23 0.13 0.08
106

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

Sat, WinterDesign 0.11 0.1 0.08 0.06 0.06 0.06 0.07 0.2 0.24 0.27 0.42 0.54 0.59 0.6 0.49 0.48 0.47 0.46 0.44 0.36 0.29 0.22 0.16 0.13

Sun, Hol, Other 0.07 0.07 0.07 0.06 0.06 0.06 0.07 0.1 0.12 0.14 0.29 0.31 0.36 0.36 0.34 0.35 0.37 0.34 0.25 0.27 0.21 0.16 0.1 0.06

Water Equipment Latent fract sched All 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05 0.05

Water Equipment Sensible fract 

sched All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

Water Equipment Hot Supply Temp 

Sched All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49

Water Equipment Temp Sched All 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49 49

PlantOnSched All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

SWHSys1 Water Heater Ambient 

Temperature Schedule Name All 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22 22

SWHSys1 Water Heater Setpoint 

Temperature Schedule Name All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60

SWHSys1-Loop-Temp-Schedule All 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60 60
107

Table B-16 Warehouse Hourly Operation Schedules 

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

BLDG_EQUIP_SCH WD 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.5 0.8 0.9 0.9 0.9 0.8 0.9 0.9 0.9 0.9 0.4 0.1 0.1 0.1 0.1 0.1 0.1

Sat 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.2 0.4 0.4 0.4 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

BLDG_LIGHT_SCH WD 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.4 0.7 0.9 0.9 0.9 0.8 0.9 0.9 0.9 0.9 0.3 0.1 0.1 0.1 0.1 0.1 0.1

Sat 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.24 0.24 0.24 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

BLDG_OCC_SCH WD 0 0 0 0 0 0 0 0.15 0.7 0.9 0.9 0.9 0.5 0.85 0.85 0.85 0.2 0 0 0 0 0 0 0

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Sat 0 0 0 0 0 0 0 0 0.2 0.2 0.2 0.2 0.1 0.1 0.1 0.1 0 0 0 0 0 0 0 0

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

CLGSETP_FineStorage_SCH All 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7

CLGSETP_SCH WD, SummerDesign 30 30 30 30 30 30 30 24 24 24 24 24 24 24 24 24 24 30 30 30 30 30 30 30

Sat 30 30 30 30 30 30 30 30 24 24 24 24 24 24 24 24 30 30 30 30 30 30 30 30

Other 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30

Dual Zone Control Type Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

HTGSETP_BulkStorage_SCH All 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2

HTGSETP_FineStorage_SCH All 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

HTGSETP_SCH WD 15.5 15.5 15.5 15.5 15.5 15.5 21 21 21 21 21 21 21 21 21 21 21 15.5 15.5 15.5 15.5 15.5 15.5 15.5

WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

Sat 15.5 15.5 15.5 15.5 15.5 15.5 15.5 21 21 21 21 21 21 21 21 21 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5

Other 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5

HVACOperationSchd WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0

Sat, WinterDesign 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

MinOA_Sched WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0

Sat, WinterDesign 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2

BLDG_EQUIP_SCH WD 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.5 0.8 0.9 0.9 0.9 0.8 0.9 0.9 0.9 0.9 0.4 0.1 0.1 0.1 0.1 0.1 0.1

Sat 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.2 0.4 0.4 0.4 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1
108

Schedule Day of Week 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

BLDG_LIGHT_SCH WD 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.4 0.7 0.9 0.9 0.9 0.8 0.9 0.9 0.9 0.9 0.3 0.1 0.1 0.1 0.1 0.1 0.1

Sat 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.24 0.24 0.24 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1 0.1

BLDG_OCC_SCH WD 0 0 0 0 0 0 0 0.15 0.7 0.9 0.9 0.9 0.5 0.85 0.85 0.85 0.2 0 0 0 0 0 0 0

SummerDesign 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

Sat 0 0 0 0 0 0 0 0 0.2 0.2 0.2 0.2 0.1 0.1 0.1 0.1 0 0 0 0 0 0 0 0

WinterDesign 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

Sun, Hol, Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

CLOTHING_SCH All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

All 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5 0.5

All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

WORK_EFF_SCH All 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

CLGSETP_FineStorage_SCH All 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7 26.7

CLGSETP_SCH WD, SummerDesign 30 30 30 30 30 30 30 24 24 24 24 24 24 24 24 24 24 30 30 30 30 30 30 30

Sat 30 30 30 30 30 30 30 30 24 24 24 24 24 24 24 24 30 30 30 30 30 30 30 30

Other 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30 30

Dual Zone Control Type Sched All 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4 4

HTGSETP_BulkStorage_SCH All 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2 7.2

HTGSETP_FineStorage_SCH All 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6 15.6

HTGSETP_SCH WD 15.5 15.5 15.5 15.5 15.5 15.5 21 21 21 21 21 21 21 21 21 21 21 15.5 15.5 15.5 15.5 15.5 15.5 15.5

WinterDesign 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21 21

Sat 15.5 15.5 15.5 15.5 15.5 15.5 15.5 21 21 21 21 21 21 21 21 21 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5

Other 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5 15.5

HVACOperationSchd WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0

Sat, WinterDesign 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

MinOA_Sched WD, SummerDesign 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0

Sat, WinterDesign 0 0 0 0 0 0 0 1 1 1 1 1 1 1 1 1 0 0 0 0 0 0 0 0

Other 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

ALWAYS_ON All 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1 1

ACTIVITY_SCH All 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120 120

AIR_VELO_SCH All 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2 0.2
F1147-E(10/2008)

REPORT DOCUMENTATION PAGE Form Approved

OMB No. 0704-0188

The public reporting burden for this collection of information is estimated to average 1 hour per response, including the time for reviewing instructions, searching existing data sources, 

gathering and maintaining the data needed, and completing and reviewing the collection of information. Send comments regarding this burden estimate or any other aspect of this 

collection of information, including suggestions for reducing the burden, to Department of Defense, Executive Services and Communications Directorate (0704-0188). Respondents 

should be aware that notwithstanding any other provision of law, no person shall be subject to any penalty for failing to comply with a collection of information if it does not display a 

currently valid OMB control number.

PLEASE DO NOT RETURN YOUR FORM TO THE ABOVE ORGANIZATION.

1. REPORT DATE (DD-MM-YYYY)

February 2011

2. REPORT TYPE

Technical Report

3. DATES COVERED (From - To)

4. TITLE AND SUBTITLE

U.S. Department of Energy Commercial Reference Building Models 

of the National Building Stock

5a. CONTRACT NUMBER

DE-AC36-08GO28308

5b. GRANT NUMBER

5c. PROGRAM ELEMENT NUMBER

6. AUTHOR(S)

Michael Deru, Kristin Field, Daniel Studer, Kyle Benne, Brent 

Griffith, and Paul Torcellini (National Renewable Energy Laboratory)

Bing Liu, Mark Halverson, Dave Winiarski, and Michael Rosenberg

(Pacific Northwest National Laboratory)

Mehry Yazdanian (Lawrence Berkeley National Laboratory)

Joe Huang (Formerly of Lawrence Berkeley National Laboratory)

Drury Crawley (Formerly of the U.S. Department of Energy)

5d. PROJECT NUMBER

NREL/TP-5500-46861

5e. TASK NUMBER

BEC7.1304

5f. WORK UNIT NUMBER

7. PERFORMING ORGANIZATION NAME(S) AND ADDRESS(ES)

National Renewable Energy Laboratory

1617 Cole Blvd.

Golden, CO 80401-3393

8. PERFORMING ORGANIZATION

REPORT NUMBER

NREL/TP-5500-46861

9. SPONSORING/MONITORING AGENCY NAME(S) AND ADDRESS(ES) 10. SPONSOR/MONITOR'S ACRONYM(S)

NREL

11. SPONSORING/MONITORING

AGENCY REPORT NUMBER

12. DISTRIBUTION AVAILABILITY STATEMENT

National Technical Information Service

U.S. Department of Commerce

5285 Port Royal Road

Springfield, VA 22161

13. SUPPLEMENTARY NOTES

14. ABSTRACT (Maximum 200 Words)

The U.S. Department of Energy (DOE) Building Technologies Program has set the aggressive goal of producing 

marketable net-zero energy buildings by 2025. This goal will require collaboration between the DOE laboratories and 

the building industry. We developed standard or reference energy models for the most common commercial 

buildings to serve as starting points for energy efficiency research. These models represent fairly realistic buildings 

and typical construction practices. Fifteen commercial building types and one multifamily residential building were 

determined by consensus between DOE, the National Renewable Energy Laboratory, Pacific Northwest National 

Laboratory, and Lawrence Berkeley National Laboratory, and represent approximately two-thirds of the commercial 

building stock.

15. SUBJECT TERMS

net-zero energy; reference building; energy efficiency; energy simulation

16. SECURITY CLASSIFICATION OF: 17. LIMITATION 

OF ABSTRACT

UL

18. NUMBER 

OF PAGES

19a. NAME OF RESPONSIBLE PERSON

a. REPORT

Unclassified

b. ABSTRACT

Unclassified

c. THIS PAGE

Unclassified 19b. TELEPHONE NUMBER (Include area code)

Standard Form 298 (Rev. 8/98)

Prescribed by ANSI Std. Z39.18