# EMISSIONS TEST REPORT

POLK POWER S T ATION UNIT 1 FACILITY ID NUMBER: 1050233 EMISSION UNIT ID NO: -001

SULFURIC ACID MIST (SAM)

May 18, 2005

Prepared For: Tampa Elec tric Compa n y Polk P o wer Station P.O. Box 1 11 Tampa, Florida 33601-0111

Prepared By: Tampa Elec tric Compa n y Environme n tal A ffairs Department Environme n tal Service s , Air Services Group

Envi ronme n tal Servi c es Ai r Servi c es Grou p 5010 Cau s e w ay Boul eva r d Tampa, Fl ori da 336 19- 6 1 30

## REPORT CERTIFICATION

I ha ve revi ewed the t e st perfor ma nce, associated quality assura nce activities, the resulta n t calculations, a n d the contents of this repor t , a n d certify that a ll proj ect quality obj ectives have been met. Th is r

e port is approved for submitta l.

Signature:__________________________ Raymond A

. McDarby, Jr. Senior Envi ronmenta l Technician Quality Assurance/Quality Control Specialist Air Services Group Environme n tal Health & Safety Tampa Elec tric Compa n y

The sampling and subseque nt da ta entry/reduction det a iled in this report were cond ucted at m y d i rection

, and I here by certif y

t h at t h is tes t report is authentic and accurate to t h e best of my knowledge.

Signature:__________________________ Juan F. Ramirez Enviro nme n tal Techni cian Test Team Lead Air Services Group Environme n tal Health & Safety Tampa Elec tric Compa n y

I ha ve revi ewed the t e sting deta ils and results subm itt e d in t h is r e port, and hereby certify that this test report is authenti c and accurate to the best of my k n owle dge.

Signature:__________________________ Davi d A

. S m ith Coordi nator – Air Services Group Environme n tal Health & Safety Tampa Elec tric Compa n y

## TABLE OF CONTENTS

SECTION PAGE NO.
1.0 INTRODUCTION 1
2.0 DISCUSSION OF RESULTS 2
3.0 SOURCE DESCRIPTION/TEST PROCEDURES 3
4.0 TABULATED RESULTS REFERENCE METHOD 8 (SULFURIC ACID MIST) RESULTS 5
SULFUR DIOXIDE AND OXIDES OF NITROGEN FROM CEMS 6
5.0 SAMPLING LOCATION / TRAVERSE DIAGRAM
STACK SAMPLING LOCATION 8

APPENDICES
A. SULFURIC ACID MIST TEST INFORMATION CALCULATED DATA FIELD DATA SHEETS LABORATORY ANALYSIS EQUIPMENT CALIBRATIONS

B. PLANT OPERATIONAL DATA

C. TEST PARTICIPANTS

### 1 

## 1.0 INTRODUCTION

On May 18, 2005, Tampa Electric Company’s , Environmental Services, Air Services Group performed Sulfuric Acid Mist (SAM) sour ce emission tests on Unit No. 1 at the
Polk Power Station. Unit No. 1 is an integrated coal gas ification combined cycle (IGCC) generating unit. The combustion turbine was fired with syngas from the coal gasification system. A blend of petroleum coke and bituminous coal was gasified for this test. Testing was conducted according to United States Envi ronmental Protection Agency (USEPA) test methods stipulated in 40 CFR Part 60, Appendix A and Florida Department of Environmental Protecti on (FDEP) Permit No. 1050233-016-AV.

### 2 

## 2.0 DISCUSSION OF RESULTS

The Sulfuric Acid Mist (H 2 

### SO 4 

### ) emission rate was derived from three 1-hour test runs. The calculated average H 2 

### SO 4 

### emission rate was 22 lbs/hr. The FDEP permitted emission rate is 55 lbs/hr based on a 30-day rolling average.

Sulfur Dioxide (SO 2 

### ) concentration and emissions during t he sulfuric acid mist testing
were determined to be 0.146 lb/mmBtu and 251 lbs/hr.

Nitrogen Oxides (NOx) concentration and emissions during the sulfuric acid mist testing
were determined to be 0.043 lb/mmBtu and 74 lbs/hr.

During the tests on May 18, 2005, Unit No . 1 Combustion Turbine was operated at an average load of 175 megawatts and an average heat input of 1719 mmBtu/hr. The FDEP permitted heat input is 1755 mmBtu/hr, at an ambient temperature of 59o (corrected to 1749 mmBtu/hr based on an average inlet vane temperature of 86oF, and the manufacturer’s heat input correction curv e for this unit). The calculated capacity factor during the test was 98%.

### 3 

## 3.0 SOURCE DESCRIPTION/TEST PROCEDURES

Polk Power Electrical Generat ing Station is located at County Road 630 approximately 13 miles southwest of Bartow, Po lk County, Florida. Unit No. 1 is an IGCC generating unit, with a net capacity of 192 MW when fir ed with Syngas fuel. The source sampling
location consists of a circular stack 19 feet in diameter with four sample ports located 90 degrees apart on the stack circumfe rence. A diagram of the stack sampling location is included along with other pertinent information on the test site.

Sulfuric acid mist sampling and analysi s was performed in accordance with USEPA Reference Method 8 (40 CFR Part 60, Appendix A) "Determinati on of Sulfuric Acid Mist
and Sulfur Dioxide Emissions from Stat ionary Sources”, and FDEP Permit No. 1050233- 016-AV, Condition A.56. A USEPA audit sa mple (Request Number/Sample Number M08-2152-02/H0268) supplied by FDEP, was analyzed and reported as 19.1 mg
H 2 

### SO 4 

### /dscm.

Sulfur Dioxide and Nitrogen Oxides emissi ons data were taken from the Plant Information (PI) server system. This data wa s taken as 1-hour averages over the time frame from 8:10 through 12:10, representing the time frame of the sulfuric acid mist test.

Plant operational data was taken from the Plant Information (PI) server system. This data was taken as 1-minute averages over the time period from 8:10 through 12:10, representing time frame of the sulfuric acid mist test. Data captured included the hourly average unit load, average fuel flow, and hourly average inlet vane temperature. Details are included in Appendix B.

### 4 

## 4.0 TABULATED RESULTS

### Environmental Services Air Ser v ices Gro u p

40 C F R 60 , Append ix A - T e s t M e t h ods Re fe re nc e Me tho d 8 T e s t S u mma ry

Customer: P olk Pow e r Sta t io n Fa cility: Unit 1 Sa m p ling Loca t ion : S t a ck Operating Conditio ns: Full Loa d
Te st D a t e : M a y

18, 20 05 Run #1 Run #2 R un #3 Ave r ag e Ga s Flow R a tes Q s , a c f m : 136215 6.3 13827 36.2 1 3 72630.8 1372507.7 9 Q s( st d ) , dscfm: 859801 .0 8657 52.5 8 58127.7 861227.0 8 Sa mpled V olume, V m(s t d) , dscf: 38.21 38.63 38.04 38.29 5 Stack Moisture, B ws x 100, %: 5.30 6.08 6.22 5.86 9 Isok inetic Sa m p l i n g R a t e , I, %: 99.2 9 9

. 6 9 9 99.2 7

E H2S O 4 , lbs/hr: 21.575 75 20.5 7571 2 2 .47085 21.5407 7



### 5POLKPOWER STATIONPLANT OPERATIONAL DATAStartTime:05/18/2005 8:10EndTime:05/18/2005 12:10Time Interval:1 hrPlant Information Source:bbnd-1pisrvbbnd-1pisrvbbnd-1pisrvbbnd-1pisrvbbnd-1pisrvpolk-1pisrvPoint:P-1CEMW13XP-1CEMK07XP-1CEMG02XP-1CEMG01XP-1CEMG10X1TMSTI922MPoint Explanation:Unit1 LoadUnit1 H.I.,mmBtu/hrUnit1 SO2, lbs/mmBtuUnit1 SO2,lbs/hrUnit1 NOx, lbs/mmBtuUnit 1Inlet Temp18-May-05 08:10:00175.10147091703.6999510.1400800238.39999390.043031181.978118918-May-05 09:10:00175.10147091735.0000000.1428266248.19999690.042115583.580215518-May-05 10:10:00175.10147091711.4000240.1739555297.39999390.043946786.562698418-May-05 11:10:00175.10147091721.8000490.1350444231.89999390.043031188.813392618-May-05 12:10:00175.10147091723.5999760.1377911237.30000310.042115591.1859207Averages:175.1014711719.1000000.145940250.6399960.04284886.424069NOx, lbs/hrwill be reported asaverage Unit 1heatinput (mmBtu/hr) times the average Unit1NOxemissionrate (lb/mmBtu).UNIT# 1COMBINED CYCLE COMBUSTIONTURBINE - FIRING SYNGASMay 18,2005Notationsto Data:All data istakenfrom Plant Information (PI) servers. The bbnd-1pisrv is the official repository for all CEMrelated data.6

### 7 

## 5.0 SAMPLING LOCATION TRAVERSE DIAGRAM

### 8 UN F I RE D H E AT

RE CO VE RY

BO I L E R T R AN SI T I O N

DU CT

EX HA US T F R O M TU R B I N E 1 4 FT.

3 8 FT. 15 0

F T

.

13 6

F T

.

P O RT L O CA T I O N P L A N 1 9

. 0 FT. I D

.

ST AC K D I AM ET ER S D O W N S T R E A M FR O M D I ST UR BAN CE = 2. 0
S T A C K D I AM ET ER S U P S T R E A M FR O M D I S T U R BA N C E = 0.7 ST AC K D I AM E T E R = 1 9

. 0 F T

. S T A C K A R E A = 28 3.5 29 S Q

. F T

. ST AC K A R E A = 4 0 8 2 8

. 1 38 SQ

. I N

.

TR A V ER S E P O I N T S 1

- 4.7 9 ” 2

- 1 5 .2 8 ” 3

- 2 6 .9 0 ” 4

- 4 0 .3 6 ” 5

- 5 7 .0 0 ” 6

- 8 0 .1 7 ”

AD D 1 3 ” PO RT L E NG T H TO P O I N T S 

### Po l k Po we r St a t io n
Un i t No

. 1
IG CC

T e st Lo ca t i on

## APPENDIX A SULFURIC ACID MIST TEST INFORMATION

## CALCULATED DATA

### Environmental Services A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 1 Date: 05/18/05

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.197 inches Barometric Pressure, P b : 29.80 "Hg Nozzle Area, A n : 0.00021166 ft 2
Stack Pressure, P s : 29.73 "Hg Average Orifice Meter, ∆ H: 1.280 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 38.921 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 75.3 o F Gas Analysis: 7.7 % CO 2 Average Stack Temp., T s : 327.0 o F
10.7 % O 2 Average √ ∆ p: 1.168 "H 2 O

0.0 % CO Condensate Volume, V lc : 45.4 ml 81.6 % N 2 Meter Box Y: 0.996 dimensionless

Data Calculated from Source Measurements:
V w(std) = 4.714E-02 x V lc 2.140 scf
V m(std) = 17.647 x V m x Y x (P b + ( ∆ H / 13.6)) / (T m +460) 38.207 dscf
B ws = V w(std) / (V m(std) + V w(std) ) 0.053 %
FDA = 1.0 - B ws 0.947 %
M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.66 lb./lb. mole
M s = (M d x FDA) + (18.0 x B ws ) 29.04 lb./lb. mole

v s = 85.49 x C p x ( √∆ p) x ( √ (T s + 460) / (M s x P s )) 80.07 ft/second Q s = v s x A s x 60 1362156.3 acf/minute Q s(std) = Q s x FDA x (528 / (T s + 460)) x (P s / 29.92)) 859801.0 dscf/minute I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s x 60 99.2 %

Data from Laboratory Analysis: H 2 SO 4 Normality of Barium Chloride titrant, N 0.00963 Volume Titrant Blank, V tb 0.01 Volume Titrant Sample, V t 3.08 Volume of Sample Aliquot, V a 100 Total Volume of Solution, V soln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 4.182E-07 lb/dscf
F c -factor = 2310 dscf/mmBtu
E H2SO4 = C H2SO4 x Q s(std) x 60 = 21.5757 lb/hr

### Environmental Services A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 2 Date: 05/18/05

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.197 inches Barometric Pressure, P b : 29.84 "Hg Nozzle Area, A n : 0.00021166 ft 2
Stack Pressure, P s : 29.77 "Hg Average Orifice Meter, ∆ H: 1.314 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 39.290 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 75.1 o F Gas Analysis: 7.7 % CO 2 Average Stack Temp., T s : 327.9 o F
10.7 % O 2 Average √ ∆ p: 1.184 "H 2 O

0.0 % CO Condensate Volume, V lc : 53.1 ml 81.6 % N 2 Meter Box Y: 0.996 dimensionless

Data Calculated from Source Measurements:
V w(std) = 4.714E-02 x V lc 2.503 scf
V m(std) = 17.647 x V m x Y x (P b + ( ∆ H / 13.6)) / (T m +460) 38.633 dscf
B ws = V w(std) / (V m(std) + V w(std) ) 0.061 %
FDA = 1.0 - B ws 0.939 %
M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.66 lb./lb. mole
M s = (M d x FDA) + (18.0 x B ws ) 28.95 lb./lb. mole

v s = 85.49 x C p x ( √∆ p) x ( √ (T s + 460) / (M s x P s )) 81.28 ft/second Q s = v s x A s x 60 1382736.2 acf/minute Q s(std) = Q s x FDA x (528 / (T s + 460)) x (P s / 29.92)) 865752.5 dscf/minute I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x 99.6 %

Data from Laboratory Analysis: H 2 SO 4 Normality of Barium Chloride titrant, N 0.00963 Volume Titrant Blank, V tb 0.01 Volume Titrant Sample, V t 2.95 Volume of Sample Aliquot, V a 100 Total Volume of Solution, V soln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 3.961E-07 lb/dscf
F c -factor = 2310 dscf/MMBtu
E H2SO4 = C H2SO4 x Q s(std) x 60 = 20.5757 lb/hr

### Environmental Services A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 3 Date: 05/18/05

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.197 inches Barometric Pressure, P b : 29.84 "Hg Nozzle Area, A n : 0.00021166 ft 2
Stack Pressure, P s : 29.77 "Hg Average Orifice Meter, ∆ H: 1.296 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 38.820 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 76.9 o F Gas Analysis: 7.7 % CO 2 Average Stack Temp., T s : 328.0 o F
10.7 % O 2 Average √ ∆ p: 1.175 "H 2 O

0.0 % CO Condensate Volume, V lc : 53.5 ml 81.6 % N 2 Meter Box Y: 0.996 dimensionless

Data Calculated from Source Measurements:
V w(std) = 4.714E-02 x V lc 2.522 scf
V m(std) = 17.647 x V m x Y x (P b + ( ∆ H / 13.6)) / (T m +460) 38.045 dscf
B ws = V w(std) / (V m(std) + V w(std) ) 0.062 %
FDA = 1.0 - B ws 0.938 %
M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.66 lb./lb. mole
M s = (M d x FDA) + (18.0 x B ws ) 28.94 lb./lb. mole

v s = 85.49 x C p x ( √∆ p) x ( √ (T s + 460) / (M s x P s )) 80.69 ft/second Q s = v s x A s x 60 1372630.8 acf/minute Q s(std) = Q s x FDA x (528 / (T s + 460)) x (P s / 29.92)) 858127.7 dscf/minute I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x 99.0 %

Data from Laboratory Analysis: H 2 SO 4 Normality of Barium Chloride titrant, N 0.00963 Volume Titrant Blank, V tb 0.01 Volume Titrant Sample, V t 3.2 Volume of Sample Aliquot, V a 100 Total Volume of Solution, V soln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 4.364E-07 lb/dscf
F c -factor = 2310 dscf/MMBtu
E H2SO4 = C H2SO4 x Q s(std) x 60 = 22.4708 lb/hr

## FIELD DATA SHEETS

## LABORATORY ANALYSIS

## Laboratory Services
5012 Causeway Blvd * Tampa Fl. 33619 * Ph (813)630-7378 * Fax (813)630-7360 * DOH #E54272
Report For: 

## Laboratory ID: AA76175

Date and Time Collected: Sampled By: 

### Sample Information Description: 

### Location Code: 05/31/2005 Report Date:

Polk No. 1 Acid Mist Comp on Syngas 

### TE_PPS_1_SAM_SYNGAS

Project Account Code: 05/19/2005 Date of Sample Receipt: Sample Collection Method:


### Laboratory Results 05/19/2005 11:13:00 AM

Result PARAMETER Qualifier Code Test Method Analyst Units Upper Limit MDL Violation Check Analysis Date & Time Lower Limit Normality of BaCl2 * 2H2O 0.0001 MM 0.00963 05/19/2005 8:00:00 AM
SO3 emission rate, lbs/hr lbs/hr EPA - RM8 RAM 22 0 5/31/2005 12:31:00 P M SO3, Avg. of Blank Titrations milliliters 0.01 EPA - Meth.8 MM 0.01 I 05/19/2005 8:00:00 AM SO3, Run #1, Avg. of Titrat ions milliliters 0.01 EPA - Meth.8 MM 3.08 05/19/2005 8:00:00 AM SO3, Run #2, Avg. of Titrat ions milliliters 0.01 EPA - Meth.8 MM 2.95 05/19/2005 8:00:00 AM SO3, Run #3, Avg. of Titrat ions milliliters 0.01 EPA - Meth.8 MM 3.20 05/19/2005 8:00:00 AM
SO3, Volume of Contained Sa mple milliliters 1 EPA - Meth.8 MM 500 05/19/2005 8:00:00 AM SO3, Volume of Sample Ali quot milliliters 0.1 EPA - Meth.8 MM 100 05/19/2005 8:00:00 AM 

### Comments

Data Qualifier Codes Explanation:



### Robert Dorey, Manager, Laboratory Services I - The reported value is between the laboratory method detection limit (MDL) and the laboratory practical quantitation limit ( PQL). PQL = 4 x MDL.
Subcontracted Laboratories:

A ll results calculated on a wet to wet basis

, unless otherwise indicated.

Report Number: -053105- 12 AA76175 Page 1 of 1 Laboratory Services certifies that the te st results in this report meet all require ments of the NELAC standards, unless indicat ed otherwise in the body of the report.

## EQUIPMENT CALIBRATIONS

## SUMMARY OF E Q UIPMENT CALIBRATION S

EQUIPMENT CAL DATE METHOD RESULTS CONSOLE (MB 07) INITIA L 04/08/2005 USEPA RM 5 0.996 POST TEST 05/18/2005 (ORIFICE) 1.000

NOZZLE SN06 INITIA L 01/10/2005 CALIPER 0.197 POST TEST 05/19/2005 MEASUREMENTS 0.197

PYROMETER (PY 06) 04/01/2005 ASTM THERMOMETER + 2 o 

### F

PITOT TUBE 05 04/08/2005 USEPA RM 2 C p 

### = 0.84

BAROMETER (BR 02) 04/05/2005 NWS COMPARISON + 0.01" Hg

### Environmental Services Air Services Group

Blue Team Manufacturer: Thermo Anderson Calibration Date: Model Number : MST-C1 Barometric Pressure: 30.2 "Hg Instrument Code Number: ^MB07 Theoretical Critical Vacuum: 14.25 "Hg L abWorks Sample Number: Calibrated By:

Initial Final Total ∆ H Time Volume Volume Volume Inlet Outlet Inlet Outlet "H 2 

### O Minutes f t 3 

### f t 3 

### f t 3 

### oF oF oF oF 0.62 15 6.110 12.977 6.867 75 73 75 73 1.10 15 12.977 22.133 9.156 76 74 77 74 1.90 15 22.133 33.932 11.799 78 74 81 75 3.60 15 33.932 50.142 16.210 81 75 88 77

Orifice K' A ctual Serial Orifice Vacuum Initial Final Average Number Coefficient "Hg oF oF oF 48 0.3483 21.5 74 74 74.0 55 0.4660 20.0 74 74 74.0 63 0.5971 18.5 74 74 74.0 73 0.8177 15.5 74 74 74.0

Dry Gas Meter Calibration Calibration Volume Volume Volume Y ∆ H α Corrected Corrected Nominal Value QA/QC Value QA/QC
Vm (std) , ft 3 Vcr (std) , ft 3 Vcr (std) , ft 3 

### (ratio) + 0.02 "H 2 

### O + 0.2
6.861 6.828 6.844 0.995 -0.001 1.680 -0.028 9.137 9.135 9.157 1.000 0.004 1.661 -0.047 11.759 11.705 11.733 0.995 -0.001 1.742 0.034 16.124 16.030 16.068 0.994 -0.002 1.749 0.041 Averages: 0.996 1.708

Review/Approval: Date:

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02.

` 

### Critical Orifice Readings Ambient Temperatures

CALCULATED DATA Critical Orifice IMPORTANT Dry Gas Meter Readings Initial Temperatures Final Tempertures

8-Apr-2005 

### USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method Quarterly Calibration

04/05/2005

JAV

IMPORTANT For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above. The Critical Orifice Coefficient, K', should be in English units.

### Environmental Services Air Services Group

Manufacturer: Thermo Calibration Date: Model Number:MST Barometric Pressure: 29.8 "Hg Instrument Code Number: MB07 Theoretical Critical Vacuum: 14.06 "Hg LabWorks Sample Number: Calibrated By: A ssociated Test: Team: BLUE

Initial Final Total ∆ H Time Volume Volume Volume Inlet Outlet Inlet Outlet "H 2 

### O Minutes ft 3 

### ft 3 

### ft 3 

### oF oF oF oF 1.10 10 746.812 752.894 6.082 73 72 74 72 1.10 10 763.124 769.211 6.087 74 73 74 73 1.10 10 769.211 775.305 6.094 74 73 73 74

Orifice K' A ctual Serial Orifice Vacuum Initial Final Average Number Coefficient "Hg oF oF oF 55 0.4660 18.0 74 72 73.0 55 0.4660 18.0 72 72 72.0 55 0.4660 18.0 72 73 72.5

Dry Gas Meter Calibration Calibration Volume Volume Volume Y ∆ H α Corrected Corrected Nominal Value QA/QC Value QA/QC
Vm (std) , ft 3 Vcr (std) , ft 3 Vcr (std) , ft 3 

### (ratio) + 0.02 "H 2 

### O + 0.2

6.017 6.015 6.099 1.000 0.000 1.688 0.003 6.014 6.021 6.093 1.001 0.001 1.683 -0.002 6.021 6.018 6.096 0.999 -0.001 1.684 -0.001 Averages: 1.000 1.685 Prior Y: 0.996 % Difference: -0.41%

Review/Approval: Date: Polk Unit 1 RM8
IMPORTANT

IMPORTANT For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above. The Critical Orifice Coefficient, K', should be in English units.



### Ambient Temperatures Dry Gas Meter Readings Final Tempertures Initial Temperatures

Critical Orifice Readings 

### USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

Jorge A Varino 05/18/2005 

### POST - TEST CALIBRATION CHECK

23-May-2005 CALCULATED DATA

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02.
For Calibration ∆ H α , the acceptable tolerance of individual values from the average is + 0.2. 

### Critical Orifice

### Environmental Service s A ir Services Grou p

QUARTERLY NOZZLE CALIBRATIONS Shared Resource STEEL NOZZLE SET

Calibration Date: 01/10/2005 Responsible Party: Jorge A. Varino

Nozzle Nozzle Diameter, D n Maximum 

### (cm) Average
I.D. D 1 

### D 2 

### D 3 Difference, " 

### D n 

### , inches
^SN01 0.300 0.300 0.300 0.000 0.118 ^SN04 0.320 0.320 0.320 0.000 0.126 ^SN05 0.380 0.380 0.380 0.000 0.150 ^SN06 0.500 0.500 0.500 0.000 0.197 ^SN09 0.697 0.700 0.700 0.001 0.275 ^SN10 0.750 0.755 0.750 0.002 0.296 ^SN12 0.985 0.990 0.990 0.002 0.389 ^SN15 0.420 0.420 0.420 0.000 0.165 ^SN16 0.505 0.505 0.505 0.000 0.199 ^SN19 0.725 0.730 0.730 0.002 0.287 ^SN22 0.940 0.935 0.940 0.002 0.369 ^SN30 0.790 0.800 0.800 0.004 0.314 ^SN36 0.480 0.475 0.480 0.002 0.188 ^SN37 0.530 0.530 0.530 0.000 0.209 ^SN38 0.640 0.640 0.645 0.002 0.253 ^SN46 0.485 0.480 0.485 0.002 0.190 ^SN47 0.515 0.520 0.515 0.002 0.203 ^SN48 0.640 0.645 0.640 0.002 0.253 ^SN50 0.790 0.795 0.795 0.002 0.312 ^SN58 0.615 0.620 0.615 0.002 0.243 ^SN68 0.625 0.630 0.630 0.002 0.247 ^SN69 0.945 0.950 0.945 0.002 0.373 ^SN70 1.560 1.560 1.560 0.000 0.614 ^SN71 1.555 1.560 1.560 0.002 0.614 ^SN72 0.955 0.950 0.950 0.002 0.375 ^SN73 1.290 1.290 1.285 0.002 0.507 ^SN74 1.240 1.245 1.245 0.002 0.490 Data Notations: All micometer readings are converted from cm to inches by multiplying by 0.393700787. Maximum Difference must be < 0.004".



### QA/QC Review by: 13-Jan-05

### Environmental Service s A ir Services Grou p

POST TEST NOZZLE CALIBRATION Shared Resource Calibration Date: 05/19/2005 

### Calibration Personnel: CRD 

### Test Designation: Polk 1 SAM



### Nozzle Nozzle Diameter, D n Maximum 

### (cm) Average
Identifier D 1 

### D 2 

### D 3 Difference, " 

### D n 

### , inches

SN08 0.500 0.500 0.500 0.000 0.197

Data Notations: All micometer readings are converted from cm to inches by multiplying by 0.393700787. Maximum Difference must be < 0.004".



### Quarterly (pre-test) value for nozzle ID SN08 was 0.197

QA/QC Review by: 23-May-05

### Environmental Services A ir Services Group Pyrometer Calibration Red Team Pyrometer Under Test Pyrometer Number: ^PY06 Labworks Sample # 0 Calibration Date: 04/01/2005

Calibrator Information Calibrator Type/Manufacturer: Hart Scientific Calibrator Serial Number: A OA024 Date of Last Calibration: 03/11/2005 Calibration Personnel (Typed and Signature): Charles Dufeny

Calibration Data

Calibration Reference Pyrometer Point Temperature Indication Difference

1 

### 400 399 1 2 

### 212 211 1 3 

### 32 33 -1

Reference temperatures must encompass the expected range of measurement. These three points should be ~ 32 degrees, ~212 degrees, and ~ 400 degrees Farenheit. Difference is calculated as follows:

(reference temperature ) – (pyrometer indication )

Qaulity Control Data

Calibration Point Difference

1 

### Pass 2 

### Pass 3 

### Pass

Reviewer: Date: 8-Apr-2005

### c PITOT TUBE CALIBRATION DATA SHEET

Pitot Tube ID # pt05 Calibration Date: 04/08/2005 

### O p eratin g Quarter: 2 Openings Damaged?

___ Y

___ N Repaired?

____ Y ___ N ___ N/A

Alpha and Beta Angle Determinations Acceptable Limits:

α 1 0.3 degrees 

### Pass Dt 0.48 < Dt > 0.95 cm

α 2 0.2 degrees 

### Pass α < 10 degrees β 1 0 degrees 

### Pass ( α 1 measured across top impact openings) β 2 0.1 degrees 

### Pass ( α 2 measured across bottom impact openings) β 1 < 5 degrees (alongside top impact openings) Gamma, Theta, A, Z, and W Determinations β 2 < 5 degrees (alongside bottom impact openings)

ψ 0.7 degrees Z < 0.32 cm (Asin ψ )
Α 2.75 cm W < 0.08 cm (Asin ο )
Ζ 0.034 cm 

### Pass A distance between tips

ο angle of plane on side of pitots

ο 0.9 degrees ψ angle between tips W 0.043 cm 

### Pass

NOTES All measurements are taken in accordance with the requirements of 40 CFR 60 Appendix A - Test Methods, Method 2, "Determination of stack gas velocity and volumetric flow rate (Type S pitot tube)". Measurement details are found in EPA/600/4-77/027b, "Quality Assurance H andbook for Air Pollution Measurement Systems: Stationary Source Specifi Methods", sub-section 3.1.1, Procurement of Apparatus and Supplies.

Comments: REMOVABLE

Printed Name: Jorge A Varino Date: 04/08/2005

Quality Assurance Review / Approval: Date: 11-Apr-05

5010 Causeway Blvd., Tampa, FL. 33619

### Environmental Services Air Services Group

BAROMETER CALIBRATION Red Team Instrument Number: BR02 Calibration Date: 04/05/2005 Calibration Personnel: CRD

Barometer Readin g Reference Readin g Difference T ime Inches Mercury Inches Mercury "H g 9:53 30.20 30.19 0.01 10:53 30.23 30.20 0.03 12:53 30.22 30.19 0.03

Avera g e Difference: 0.02

Note: Barometric readin g s must a g ree within + 0.1 "H g

. Current Reference is National Weather Service, Ruskin Florida.
Comments (Note any ad j ustments):

QA/QC Review by: Date: 8-Apr-2005

## APPENDIX B PLANT OPERATIONAL DATA

### Plant Information Database Query Results

Plant Information Source: polk-1pisrv
Start Time: 05/18/2005 8:10

End Time: 05/18/2005 12:10
Time Interval: 1 Min

Tag Name: 1pwrji900 1tsyfi910 1tmsti922m Tag Explanation: Unit Load Fuel Flow Inlet Temp Tag Units: Mwe lbs/sec oF Run Average: 175.0183395 106.115718 86.5567164 18-May-05 08:10:00 174.7468414 105.397736 81.9781189 18-May-05 08:11:00 174.983078 106.208153 81.9014359 18-May-05 08:12:00 174.7975006 105.911385 82.1391525 18-May-05 08:13:00 175.2396393 105.842506 82.0624695 18-May-05 08:14:00 174.7691345 105.70063 81.9857864 18-May-05 08:15:00 174.6455231 105.923798 81.9091034 18-May-05 08:16:00 175.086441 106.367081 82.046814 18-May-05 08:17:00 174.5258179 105.430466 81.9154968 18-May-05 08:18:00 174.2941895 107.08049 81.9921799 18-May-05 08:19:00 174.8979034 106.188896 82.0688629 18-May-05 08:20:00 175.0496521 106.323738 82.145546 18-May-05 08:21:00 174.719162 106.452423 82.0491257 18-May-05 08:22:00 174.401001 105.757904 81.94133 18-May-05 08:23:00 174.0922852 105.927612 82.0953217 18-May-05 08:24:00 174.7769318 106.061378 82.4225616 18-May-05 08:25:00 175.1284332 105.813164 82.2183456 18-May-05 08:26:00 175.0068665 106.600861 82.0141373 18-May-05 08:27:00 175.7931824 106.07753 81.9137344 18-May-05 08:28:00 176.0483398 107.235329 82.0373383 18-May-05 08:29:00 175.3188934 106.840302 82.1609344 18-May-05 08:30:00 175.2060242 105.913879 82.2845383 18-May-05 08:31:00 175.839325 105.927612 82.4081421 18-May-05 08:32:00 175.7512207 106.632042 82.7783203 18-May-05 08:33:00 175.6631165 106.572227 82.6255798 18-May-05 08:34:00 175.5750275 105.45137 82.5573044 18-May-05 08:35:00 174.6391449 105.734657 82.7626266 18-May-05 08:36:00 174.6475067 106.244881 82.5470352 18-May-05 08:37:00 174.1103363 105.65477 82.5373688 18-May-05 08:38:00 174.5672455 106.875214 82.483017 18-May-05 08:39:00 175.4064026 107.507446 82.3302765 18-May-05 08:40:00 174.9261169 106.682945 82.2281265 18-May-05 08:41:00 175.2992249 105.584274 82.8035202



### Page 1 of 7

### Plant Information Database Query Results

18-May-05 08:42:00 175.9725037 106.458633 82.8139572 18-May-05 08:43:00 175.8090668 105.813164 82.8139572 18-May-05 08:44:00 175.5183716 107.70163 82.2079239 18-May-05 08:45:00 174.9350281 106.458633 82.7930832 18-May-05 08:46:00 174.8535309 105.565048 82.5162354 18-May-05 08:47:00 174.7720337 105.36454 82.7186584 18-May-05 08:48:00 174.426651 106.178665 82.6165543 18-May-05 08:49:00 174.3262329 106.96524 82.5144501 18-May-05 08:50:00 174.1914063 106.181107 82.6353989 18-May-05 08:51:00 175.2849731 105.963211 82.7906647 18-May-05 08:52:00 175.083252 105.963211 82.7574921 18-May-05 08:53:00 174.5576324 105.800636 82.8765793 18-May-05 08:54:00 175.8943481 106.682938 82.8858261 18-May-05 08:55:00 174.8249817 105.757401 82.5778351 18-May-05 08:56:00 176.1760864 106.146141 82.7318344 18-May-05 08:57:00 174.404068 105.580269 83.0398178 18-May-05 08:58:00 175.1006622 106.674698 82.692749 18-May-05 08:59:00 176.5094147 107.974281 82.9217606 18-May-05 09:00:00 174.3630676 106.185234 83.0759583 18-May-05 09:01:00 174.1436768 105.942024 82.9992752 18-May-05 09:02:00 175.0190125 105.678787 82.9225922 18-May-05 09:03:00 174.3312988 105.622421 82.8459091 18-May-05 09:04:00 174.4160156 105.648598 82.9444275 18-May-05 09:05:00 173.9946442 105.597603 83.29879 18-May-05 09:06:00 174.5283051 105.768806 83.2759399 18-May-05 09:07:00 175.0774384 105.922272 83.4453354 18-May-05 09:08:00 175.8943481 106.769348 83.596756 18-May-05 09:09:00 175.2946625 108.06942 83.2747345 18-May-05 09:10:00 175.3474121 105.73642 83.5802155 18-May-05 09:11:00 174.6009674 105.511864 83.6220093 18-May-05 09:12:00 174.8547363 105.858025 83.564415 18-May-05 09:13:00 175.3414154 106.116188 83.8749466 18-May-05 09:14:00 175.7722778 106.252632 84.0078888 18-May-05 09:15:00 175.2611389 105.85894 83.8551483 18-May-05 09:16:00 174.5222015 105.561386 83.8050766 18-May-05 09:17:00 174.8009949 106.152611 83.9603424 18-May-05 09:18:00 175.0287781 106.137466 83.814064 18-May-05 09:19:00 175.3977051 108.209633 84.0165329 18-May-05 09:20:00 175.6027374 106.636444 84.2190018 18-May-05 09:21:00 175.6270599 106.224419 83.9985962 18-May-05 09:22:00 175.4548798 106.333122 84.189949



### Page 2 of 7

### Plant Information Database Query Results

18-May-05 09:23:00 174.9879456 105.754036 84.7147827 18-May-05 09:24:00 174.114624 105.529343 84.8687744 18-May-05 09:25:00 173.9096832 105.79821 85.2640228 18-May-05 09:26:00 174.0461426 105.443672 85.2736893 18-May-05 09:27:00 173.7911682 105.842926 85.2742844 18-May-05 09:28:00 174.4566345 105.664116 84.701004 18-May-05 09:29:00 175.4487762 107.619995 84.9052124 18-May-05 09:30:00 175.7635193 106.364914 85.1094208 18-May-05 09:31:00 176.1110229 106.568497 85.3136292 18-May-05 09:32:00 175.3430481 105.824425 85.5178375 18-May-05 09:33:00 175.8830566 105.927612 85.7220459 18-May-05 09:34:00 174.6208954 105.813164 85.9262543 18-May-05 09:35:00 174.7207794 105.461823 85.7901688 18-May-05 09:36:00 175.4487152 106.064606 85.6361771 18-May-05 09:37:00 175.05336 105.971512 85.4821777 18-May-05 09:38:00 175.5450592 106.305275 85.328186 18-May-05 09:39:00 174.975647 108.06723 85.7149811 18-May-05 09:40:00 175.3637695 106.672043 86.1732101 18-May-05 09:41:00 174.7387543 105.944611 86.3779068 18-May-05 09:42:00 174.792572 106.103928 86.5318985 18-May-05 09:43:00 174.8463898 106.430489 86.3993301 18-May-05 09:44:00 174.9002075 106.629784 86.1951218 18-May-05 09:45:00 174.5448761 106.818024 85.990921 18-May-05 09:46:00 174.4368134 105.944908 86.0117493 18-May-05 09:47:00 174.3287506 105.343559 86.1144104 18-May-05 09:48:00 175.0611877 106.295357 86.2170715 18-May-05 09:49:00 175.7936401 107.649422 86.7904205 18-May-05 09:50:00 175.111618 106.739708 87.1320114 18-May-05 09:51:00 175.744812 106.082504 86.0576706 18-May-05 09:52:00 174.4489746 105.639206 86.0281067 18-May-05 09:53:00 174.9397736 105.738396 86.1808472 18-May-05 09:54:00 175.58815 106.428551 86.594017 18-May-05 09:55:00 175.9047241 106.616455 86.5425034 18-May-05 09:56:00 175.5716095 106.682945 86.3284988 18-May-05 09:57:00 174.8475647 105.642265 86.4812393 18-May-05 09:58:00 174.1567078 105.322327 86.4165802 18-May-05 09:59:00 175.441452 106.881012 86.3352585 18-May-05 10:00:00 175.4523315 107.749062 86.5188446 18-May-05 10:01:00 175.4742279 106.152786 86.7024307 18-May-05 10:02:00 176.0402222 106.108429 86.8860245 18-May-05 10:03:00 175.4389343 105.892204 87.0696106



### Page 3 of 7

### Plant Information Database Query Results

18-May-05 10:04:00 174.8483582 105.710167 87.1530075 18-May-05 10:05:00 174.079895 105.05687 87.0503464 18-May-05 10:06:00 174.3813324 105.879036 86.9476852 18-May-05 10:07:00 174.3631744 105.948669 87.188942 18-May-05 10:08:00 174.7416382 105.780952 87.0071259 18-May-05 10:09:00 175.0526123 106.353966 86.5626984 18-May-05 10:10:00 174.9595642 107.210533 86.5626984 18-May-05 10:11:00 174.9435425 106.818443 86.9436646 18-May-05 10:12:00 175.9077759 106.266365 87.1222153 18-May-05 10:13:00 174.4341888 106.236351 87.1324768 18-May-05 10:14:00 174.5222321 105.456566 86.9784851 18-May-05 10:15:00 175.1397095 106.253677 87.5020599 18-May-05 10:16:00 175.2561493 106.320839 87.5020599 18-May-05 10:17:00 174.7393951 105.981544 87.2242966 18-May-05 10:18:00 174.8213654 106.318672 87.4763947 18-May-05 10:19:00 175.0627136 106.864334 87.2505417 18-May-05 10:20:00 175.1604309 107.610397 87.8203125 18-May-05 10:21:00 175.6684113 106.553665 87.9743042 18-May-05 10:22:00 175.8531494 106.276268 88.1283035 18-May-05 10:23:00 175.1452637 106.540634 87.9218521 18-May-05 10:24:00 174.6400299 105.787323 87.7153931 18-May-05 10:25:00 175.6893158 105.698723 87.5089417 18-May-05 10:26:00 174.611969 106.125977 87.6700745 18-May-05 10:27:00 175.4365692 106.22364 87.517334 18-May-05 10:28:00 175.4365692 106.439781 87.6406555 18-May-05 10:29:00 175.972168 106.400642 87.7946472 18-May-05 10:30:00 174.879425 107.50956 87.5482559 18-May-05 10:31:00 174.705246 106.299843 87.9435043 18-May-05 10:32:00 174.6052094 106.295662 88.0975037 18-May-05 10:33:00 175.0382233 105.733055 88.3140488 18-May-05 10:34:00 174.0750427 105.250099 88.2860031 18-May-05 10:35:00 174.2286377 105.870102 87.9301987 18-May-05 10:36:00 174.0034943 105.300896 88.0835648 18-May-05 10:37:00 174.2646637 106.037476 88.2369308 18-May-05 10:38:00 175.5524292 106.56559 88.3902969 18-May-05 10:39:00 174.8943329 105.746735 88.2360992 18-May-05 10:40:00 175.6338654 107.824715 88.560524 18-May-05 10:41:00 175.2874298 106.324623 88.5808792 18-May-05 10:42:00 175.8409424 106.465958 88.5226669 18-May-05 10:43:00 175.5075531 106.440971 88.0347443 18-May-05 10:44:00 175.5661011 106.531609 87.8998795



### Page 4 of 7

### Plant Information Database Query Results

18-May-05 10:45:00 175.3798523 107.162933 88.0538712 18-May-05 10:46:00 175.2347717 106.615166 88.4718628 18-May-05 10:47:00 175.2892456 106.148865 88.7250366 18-May-05 10:48:00 175.562149 105.813164 88.5380402 18-May-05 10:49:00 175.6349487 105.889465 88.9540176 18-May-05 10:50:00 175.2063141 107.265846 88.8356705 18-May-05 10:51:00 174.3958893 105.86216 88.8154221 18-May-05 10:52:00 174.3824768 105.470734 88.8154221 18-May-05 10:53:00 174.3284454 104.865952 88.8154221 18-May-05 10:54:00 174.9167938 105.768867 88.8154221 18-May-05 10:55:00 175.1356354 105.945541 88.5978317 18-May-05 10:56:00 175.4031525 105.562332 88.3926544 18-May-05 10:57:00 175.0483704 105.853973 88.2386627 18-May-05 10:58:00 174.5466461 105.930107 88.5395203 18-May-05 10:59:00 173.9666595 105.36454 88.4414215 18-May-05 11:00:00 174.4850006 107.146965 88.4414215 18-May-05 11:01:00 175.5006561 106.45752 88.4414215 18-May-05 11:02:00 174.7728577 106.151924 88.7468567 18-May-05 11:03:00 174.7810211 105.585152 88.7593231 18-May-05 11:04:00 175.5194244 105.914101 88.8571701 18-May-05 11:05:00 175.5929565 106.970535 88.8154221 18-May-05 11:06:00 174.901123 105.610977 88.8154221 18-May-05 11:07:00 174.5503082 105.14978 88.8154221 18-May-05 11:08:00 174.4792175 106.056992 89.0947571 18-May-05 11:09:00 174.5722809 105.601936 88.4536819 18-May-05 11:10:00 174.6887665 106.570023 88.8133926 18-May-05 11:11:00 174.8525696 106.4226 88.6914291 18-May-05 11:12:00 174.3156281 105.398766 88.5694733 18-May-05 11:13:00 174.7216797 105.713066 88.4475174 18-May-05 11:14:00 175.8213959 105.628975 88.7909012 18-May-05 11:15:00 175.7216034 105.813164 88.6451416 18-May-05 11:16:00 174.7676239 106.268654 88.4627075 18-May-05 11:17:00 175.0614929 105.96904 89.0483856 18-May-05 11:18:00 174.2607574 105.540329 88.5315399 18-May-05 11:19:00 175.0154114 106.004417 89.0177231 18-May-05 11:20:00 175.4908905 106.697159 89.1285477 18-May-05 11:21:00 175.9844208 106.797394 89.1285477 18-May-05 11:22:00 174.9645996 105.697952 89.1285477 18-May-05 11:23:00 175.3720245 105.778831 88.9350739 18-May-05 11:24:00 175.4055023 106.14595 89.0878143 18-May-05 11:25:00 175.3514709 106.427895 89.0156174



### Page 5 of 7

### Plant Information Database Query Results

18-May-05 11:26:00 174.7560425 105.725876 88.861618 18-May-05 11:27:00 175.1252747 105.595398 89.0310135 18-May-05 11:28:00 174.7984009 105.071564 88.8834915 18-May-05 11:29:00 174.4715271 105.622734 88.9855957 18-May-05 11:30:00 174.4602203 106.308327 89.0877075 18-May-05 11:31:00 175.186676 106.862007 89.6869431 18-May-05 11:32:00 175.1218262 106.187241 90.0592041 18-May-05 11:33:00 175.7972412 106.568497 90.0592041 18-May-05 11:34:00 176.237381 105.927612 90.3877258 18-May-05 11:35:00 176.0267181 105.939056 90.6058807 18-May-05 11:36:00 175.2102356 106.129028 90.451889 18-May-05 11:37:00 174.838913 105.741753 90.2978973 18-May-05 11:38:00 174.5808258 105.285194 90.143898 18-May-05 11:39:00 174.8923492 105.899467 90.2388611 18-May-05 11:40:00 175.5895081 106.278572 90.1864929 18-May-05 11:41:00 175.872879 107.278053 90.4919739 18-May-05 11:42:00 175.744751 106.181107 90.5160522 18-May-05 11:43:00 174.462326 105.551857 90.0540771 18-May-05 11:44:00 174.0570831 105.411896 89.780304 18-May-05 11:45:00 174.3362579 106.126381 89.8829651 18-May-05 11:46:00 174.3712769 106.440895 89.9856262 18-May-05 11:47:00 174.7447968 106.457611 89.9719391 18-May-05 11:48:00 174.920517 105.480186 90.0207062 18-May-05 11:49:00 174.7264709 105.419479 89.8667145 18-May-05 11:50:00 174.5324097 105.548225 89.7789154 18-May-05 11:51:00 174.5177155 106.775192 89.9304199 18-May-05 11:52:00 174.9632263 105.584274 90.2001114 18-May-05 11:53:00 174.4315186 105.153961 90.6384811 18-May-05 11:54:00 174.3537292 104.774956 90.0865784 18-May-05 11:55:00 174.5923767 105.680611 90.2919083 18-May-05 11:56:00 175.3516846 105.713623 90.4972305 18-May-05 11:57:00 175.0082092 105.474411 90.9985657 18-May-05 11:58:00 175.8085938 105.890388 90.978035 18-May-05 11:59:00 175.7415619 106.421562 90.3825912 18-May-05 12:00:00 174.867157 105.495583 90.9985657 18-May-05 12:01:00 174.2344513 106.828125 90.3723221 18-May-05 12:02:00 174.8009338 105.567863 90.9882965 18-May-05 12:03:00 175.7242889 105.704514 91.2706223 18-May-05 12:04:00 175.5892029 105.85302 91.3116837 18-May-05 12:05:00 175.3612671 105.251587 91.3116837 18-May-05 12:06:00 175.3083801 105.361496 90.7662506



### Page 6 of 7

### Plant Information Database Query Results

18-May-05 12:07:00 174.6158142 105.032288 90.5508804 18-May-05 12:08:00 174.5048676 105.546867 90.3956146 18-May-05 12:09:00 174.9023438 105.65638 90.9463806 18-May-05 12:10:00 175.0937805 105.257576 91.1859207



### Page 7 of 7

## APPENDIX C TEST PARTICIPANTS

## TEST PARTICIPANTS

AIR SERVICES GROUP ENVIRONMENTAL SERVICES

Robert Barthelette Environmental Technician

Juan Ramirez Environmental Technician Jorge Varino Technician

POLK POWER STATION

Michael Perkins Environmental Coordinator