Name: Jon A Finlinson

Title: President & Chief Operations Officer

Company: Intermountain Power Service Corp

Sign Date: 8/31/2010

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

6481_INTERMOUNTAIN

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Monday, February 28, 2011 Page 1 of 33
6481_INTERMOUNTAIN

8/31/2010

Facility Information:

6481_INTERMOUNTAIN

850 West Brush Wellman Road

Delta UT 84624

Contact: Jon Christensen

Phone: (435) 864-4414

Fax: (435) 864-6670

Email: jon-c@ipsc.com

Testing Company:

Applied Environmental Consultants, a JBR company

1553 West Elna Rae

Tempe AZ 85281

Contact:Jason Nockleby

Phone: (480) 829-0457

Fax: (480) 829-8985

Email: Jnockleby@jbrenv.com

Air Permit Number:

2700010003

Permitted Source ID/Name:

6481 INTERMOUNTAIN

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

The Intermountain Power Project (IPP) consists of two 950 MWhe (gross) coal-fired thermal cycle steam-electric 

generating units. Each identical unit has a dry bottom boiler utilizing opposed wall low-NOX control burners with 

associated over-fire air for NOX reduction during combustion. Other pollution control devices (PCD) include fabric 

filter baghouses with reverse air cleaning and multi-module counterflow wet spray limestone flue gas desulfurization 

(FGD) scrubbers. 

Each IPP unit uses a continuous emissions monitoring system (CEMS) certified under both Part 75 for the Acid Rain 

Markets Program, and Part 60 New Source Performance Standard (NSPS) to monitor CO2, NOX, and SO2. Each 

unit also utilizes an uncertified mercury CEMS that measures flue gas concentrations only, since a data acquisition 

and handling system (DAHS) has not yet been integrated due to the remand of the Clean Air Mercury Rule (CAMR).

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 4902700010 FRS #: 110000470053

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

1SGA 336 0 0 336 2880 4200 4 12

Monday, February 28, 2011 Page 2 of 33
6481_INTERMOUNTAIN

8/31/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Monday, February 28, 2011 Page 3 of 33
6481_INTERMOUNTAIN

8/31/2010

Sampling / Stack Data Results Summary

Location 1SGA - EPA Method 316

Average

Run Number M316-4 M316-1 M316-2

Test Date 6/15/2010 6/15/2010 6/15/2010

Run Start Time 4:05:00 PM 8:13:00 

AM

10:40:00 AM

Run Finish Time 5:55:00 PM 10:03:00 

AM

12:30:00 PM

Net Run Time, minutes 120 120 120

Dry Gas Meter Volume Sampled, dscf 67.936 73.699 71.863 71.166

Moisture Content of Stack Gas, % 15.14 14.42 14.41 14.657

Moisture Saturation at Stack Gas Temperature, % 14.94 14.91 15.11 14.987

Carbon Dioxide, % 13.61 13.89 13.89 13.797

Oxygen, % 5.61 5.59 5.6 5.600

Average Stack Gas Temperature, °F 122.67 122.58 123.08 122.777

Dry Volumetric Flow Rate, dry scfm 1,925,301.8 2,047,060.5 2,010,431.5 1,994,264.60

0

Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,014,721.8 3,185,408.2 3,130,729.5 3,110,286.50

0

Percent Isokinetic of Sampling Rate, % 102.5 104.5 103.8 103.600

F-Factor, dscfm/MMBtu @ %O2 9658 9681 9703 9,680.667

Fw 10565 10613 10641 10,606.333

Fc 0 0 0 0.000

Monday, February 28, 2011 Page 4 of 33
6481_INTERMOUNTAIN

8/31/2010

Location 1SGA - EPA Method 316 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location 1SGA - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, % Method 10 Method 10 Method 10

Oxygen, % 6/15/2010 6/15/2010 6/15/2010

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2 CC249349-

CO

CC249349-

CO

CC249349-

CO

Moisture, %

Fuel Type 0.14 0.02 0.11

Fw 98.83 98.53 98.5 98.620

Fc -1.97 -2.12 -2.14 -2.077

Monday, February 28, 2011 Page 5 of 33
6481_INTERMOUNTAIN

8/31/2010

Location 1SGA - Method 25A

Average

Run Number 1 2 3

Test Date 6/15/2010 6/15/2010 6/15/2010

Run Start Time 8:05:00 AM 10:51:00 

AM

1:22:00 PM

Run Finish Time 10:14:00 AM 12:50:00 

PM

3:21:00 PM

Carbon Dioxide, % 13.89 13.89 13.83 13.870

Oxygen, % 5.59 5.6 5.65 5.613

Dry Volumetric Flow Rate, dry scfm 2403905 2351467 2186012 2,313,794.66

7

F-Factor, dscfm/MMBtu @ %O2 9681 9703 9719 9,701.000

Moisture, % 14.43 14.41 15.6 14.813

Fuel Type Override Override Override

Fw 10613 10641 10652 10,635.333

Fc 0 0 0 0.000

Location 1SGA - Method 25A 3

Average

Run Number 4

Test Date 6/15/2010

Run Start Time 4:01:00 PM

Run Finish Time 6:00:00 PM

Carbon Dioxide, % 14.13 14.130

Oxygen, % 5.29 5.290

Dry Volumetric Flow Rate, dry scfm 2264127 2,264,127.00

0

F-Factor, dscfm/MMBtu @ %O2 9658 9,658.000

Moisture, % 14.06 14.060

Fuel Type Override

Fw 10565 10,565.000

Fc 0 0.000

Monday, February 28, 2011 Page 6 of 33
6481_INTERMOUNTAIN

8/31/2010

Location 1SGA - Method 3A CO2

Average

Run Number 1 2 3

Test Date 6/15/2010 6/15/2010 6/15/2010

Run Start Time 8:05:00 AM 10:51:00 

AM

1:22:00 PM

Run Finish Time 10:14:00 AM 12:50:00 

PM

3:21:00 PM

Carbon Dioxide, % 13.89 13.89 13.83 13.870

Oxygen, % 5.59 5.6 5.65 5.613

Dry Volumetric Flow Rate, dry scfm 2403905 2351467 2186012 2,313,794.66

7

F-Factor, dscfm/MMBtu @ %O2 9681 9703 9719 9,701.000

Moisture, % 14.43 14.41 15.6 14.813

Fuel Type Override Override Override

Fw 10613 10641 10652 10,635.333

Fc 0 0 0 0.000

Location 1SGA - Method 3A CO2 3

Average

Run Number 4

Test Date 6/15/2010

Run Start Time 4:01:00 PM

Run Finish Time 6:00:00 PM

Carbon Dioxide, % 14.13 14.130

Oxygen, % 5.29 5.290

Dry Volumetric Flow Rate, dry scfm 2264127 2,264,127.00

0

F-Factor, dscfm/MMBtu @ %O2 9658 9,658.000

Moisture, % 14.06 14.060

Fuel Type Override

Fw 10565 10,565.000

Fc 0 0.000

Monday, February 28, 2011 Page 7 of 33
6481_INTERMOUNTAIN

8/31/2010

Location 1SGA - Method 3A O2

Average

Run Number 1 2 3

Test Date 6/15/2010 6/15/2010 6/15/2010

Run Start Time 8:05:00 AM 10:51:00 

AM

1:22:00 PM

Run Finish Time 10:14:00 AM 12:50:00 

PM

3:21:00 PM

Carbon Dioxide, % 13.89 13.89 13.83 13.870

Oxygen, % 5.59 5.6 5.65 5.613

Dry Volumetric Flow Rate, dry scfm 2403905 2351467 2186012 2,313,794.66

7

F-Factor, dscfm/MMBtu @ %O2 9681 9703 9719 9,701.000

Moisture, % 14.43 14.41 15.6 14.813

Fuel Type Override Override Override

Fw 10613 10641 10652 10,635.333

Fc 0 0 0 0.000

Location 1SGA - Method 3A O2 3

Average

Run Number 4

Test Date 6/15/2010

Run Start Time 4:01:00 PM

Run Finish Time 6:00:00 PM

Carbon Dioxide, % 14.13 14.130

Oxygen, % 5.29 5.290

Dry Volumetric Flow Rate, dry scfm 2264127 2,264,127.00

0

F-Factor, dscfm/MMBtu @ %O2 9658 9,658.000

Moisture, % 14.06 14.060

Fuel Type Override

Fw 10565 10,565.000

Fc 0 0.000

Monday, February 28, 2011 Page 8 of 33
6481_INTERMOUNTAIN

8/31/2010

Emissions Summary

Location: Stack Platform - Method 0011

Compound: Formaldehyde

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.0153 0.0109 0.0076 0.011

lb/mmBtuO2 6.42E-06 4.59E-06 3.08E-06 0.000

ppm 5.36E-03 3.85E-03 2.59E-03 0.004

ppm@7%O2 5.96E-03 4.26E-03 2.86E-03 0.004

Location: Stack Platform - Method 10

Compound: Carbon Monoxide

Average

Run PJ4 R1 PJ4 R2 PJ4 R3

Elb/hr 2.56E+00 4.43E+00 3.86E+00 3.617

lb/mmBtuO2 4.29E-04 7.55E-04 6.60E-04 0.001

mg/dscm 4.69E-01 8.16E-01 7.03E-01 0.663

Location: Stack Platform - Method 23

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.00000000501 0.00000000531 0.00000000503 0.000

lb/mmBtuO2 5.21E-13 5.57E-13 5.38E-13 0.000

ng/dscm 5.70E-04 6.02E-04 5.73E-04 0.001

ng/dscm@7%O2 6.05E-04 6.46E-04 6.24E-04 0.001

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.00000000189 0.00000000179 0.00000000176 0.000

lb/mmBtuO2 1.97E-13 1.88E-13 1.88E-13 0.000

ng/dscm 2.15E-04 2.03E-04 2.00E-04 0.000

ng/dscm@7%O2 2.28E-04 2.18E-04 2.18E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.00000000167 0.00000000177 0.00000000146 0.000

lb/mmBtuO2 1.74E-13 1.86E-13 1.56E-13 0.000

ng/dscm 1.90E-04 2.01E-04 1.66E-04 0.000

ng/dscm@7%O2 2.02E-04 2.16E-04 1.81E-04 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.00000000364 0.00000000619 0.000000006 0.000

lb/mmBtuO2 3.79E-13 6.49E-13 6.41E-13 0.000

ng/dscm 4.14E-04 7.02E-04 6.83E-04 0.001

ng/dscm@7%O2 4.39E-04 7.53E-04 7.43E-04 0.001

Monday, February 28, 2011 Page 9 of 33
6481_INTERMOUNTAIN

8/31/2010

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.0000001145 0.000000192 0.000000242 0.000

lb/mmBtuO2 1.19E-11 2.01E-11 2.59E-11 0.000

ng/dscm 1.30E-02 2.18E-02 2.76E-02 0.021

ng/dscm@7%O2 1.38E-02 2.34E-02 3.00E-02 0.022

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.000000447 0.000000728 0.000000895 0.000

lb/mmBtuO2 4.65E-11 7.63E-11 9.57E-11 0.000

ng/dscm 5.08E-02 8.25E-02 1.02E-01 0.078

ng/dscm@7%O2 5.39E-02 8.85E-02 1.11E-01 0.084

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.0000000421 0.0000000787 0.0000000943 0.000

lb/mmBtuO2 4.38E-12 8.25E-12 1.01E-11 0.000

ng/dscm 4.79E-03 8.92E-03 1.07E-02 0.008

ng/dscm@7%O2 5.08E-03 9.57E-03 1.16E-02 0.009

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.0000000282 0.0000000526 0.0000000695 0.000

lb/mmBtuO2 2.93E-12 5.52E-12 7.43E-12 0.000

ng/dscm 3.21E-03 5.96E-03 7.91E-03 0.006

ng/dscm@7%O2 3.41E-03 6.39E-03 8.61E-03 0.006

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.0000014 0.00000235 0.00000278 0.000

lb/mmBtuO2 1.46E-10 2.46E-10 2.97E-10 0.000

ng/dscm 1.59E-01 2.66E-01 3.17E-01 0.247

ng/dscm@7%O2 1.69E-01 2.85E-01 3.45E-01 0.266

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.0000000277 0.0000000543 0.0000000652 0.000

lb/mmBtuO2 2.88E-12 5.69E-12 6.97E-12 0.000

ng/dscm 3.15E-03 6.16E-03 7.42E-03 0.006

ng/dscm@7%O2 3.34E-03 6.61E-03 8.08E-03 0.006

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.00000000161 0.00000000171 0.00000000143 0.000

lb/mmBtuO2 1.68E-13 1.79E-13 1.53E-13 0.000

Monday, February 28, 2011 Page 10 of 33
6481_INTERMOUNTAIN

8/31/2010

ng/dscm 1.83E-04 1.94E-04 1.63E-04 0.000

ng/dscm@7%O2 1.94E-04 2.08E-04 1.77E-04 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.00000000125 0.00000000121 0.000000000944 0.000

lb/mmBtuO2 1.30E-13 1.27E-13 1.01E-13 0.000

ng/dscm 1.42E-04 1.37E-04 1.07E-04 0.000

ng/dscm@7%O2 1.51E-04 1.47E-04 1.16E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.00000000105 0.00000000106 0.000000000977 0.000

lb/mmBtuO2 1.09E-13 1.11E-13 1.04E-13 0.000

ng/dscm 1.19E-04 1.20E-04 1.11E-04 0.000

ng/dscm@7%O2 1.26E-04 1.29E-04 1.21E-04 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.00000000723 0.00000000486 0.00000000626 0.000

lb/mmBtuO2 7.52E-13 5.10E-13 6.69E-13 0.000

ng/dscm 8.22E-04 5.51E-04 7.13E-04 0.001

ng/dscm@7%O2 8.72E-04 5.91E-04 7.76E-04 0.001

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.00000000578 0.000000011 0.0000000106 0.000

lb/mmBtuO2 6.02E-13 1.15E-12 1.13E-12 0.000

ng/dscm 6.57E-04 1.25E-03 1.21E-03 0.001

ng/dscm@7%O2 6.97E-04 1.34E-03 1.32E-03 0.001

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.0000000981 0.000000163 0.000000161 0.000

lb/mmBtuO2 1.02E-11 1.71E-11 1.72E-11 0.000

ng/dscm 1.12E-02 1.85E-02 1.83E-02 0.016

ng/dscm@7%O2 1.19E-02 1.98E-02 1.99E-02 0.017

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.00000000688 0.0000000145 0.0000000119 0.000

lb/mmBtuO2 7.16E-13 1.52E-12 1.27E-12 0.000

ng/dscm 7.82E-04 1.64E-03 1.36E-03 0.001

ng/dscm@7%O2 8.30E-04 1.76E-03 1.48E-03 0.001

Compound: OCDD

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Monday, February 28, 2011 Page 11 of 33
6481_INTERMOUNTAIN

8/31/2010

Mass_mg 0.00000847 0.00000000577 0.00000000556 0.000

lb/mmBtuO2 8.81E-10 6.05E-13 5.94E-13 0.000

ng/dscm 9.63E-01 6.54E-04 6.33E-04 0.321

ng/dscm@7%O2 1.02E+00 7.01E-04 6.89E-04 0.340

Compound: OCDF

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.00000522 0.00000000697 0.00000000573 0.000

lb/mmBtuO2 5.43E-10 7.31E-13 6.13E-13 0.000

ng/dscm 5.94E-01 7.90E-04 6.52E-04 0.198

ng/dscm@7%O2 6.30E-01 8.47E-04 7.10E-04 0.211

Compound: Other HpCDD

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HpCDF

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDD

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0 0.00000000778 0 0.000

lb/mmBtuO2 0.00E+00 8.16E-13 0.00E+00 0.000

ng/dscm 0.00E+00 8.82E-04 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 9.46E-04 0.00E+00 0.000

Compound: Other HxCDF

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0 0.00000000237 0.00000000151 0.000

lb/mmBtuO2 0.00E+00 2.49E-13 1.61E-13 0.000

ng/dscm 0.00E+00 2.69E-04 1.72E-04 0.000

ng/dscm@7%O2 0.00E+00 2.89E-04 1.87E-04 0.000

Compound: Other PeCDD

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0 0.00000000545 0 0.000

lb/mmBtuO2 0.00E+00 5.72E-13 0.00E+00 0.000

ng/dscm 0.00E+00 6.18E-04 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 6.63E-04 0.00E+00 0.000

Monday, February 28, 2011 Page 12 of 33
6481_INTERMOUNTAIN

8/31/2010

Compound: Other PeCDF

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other TCDD

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0 0.00000000462 0.00000000231 0.000

lb/mmBtuO2 0.00E+00 4.84E-13 2.47E-13 0.000

ng/dscm 0.00E+00 5.24E-04 2.63E-04 0.000

ng/dscm@7%O2 0.00E+00 5.62E-04 2.86E-04 0.000

Compound: Other TCDF

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.00000000284 0.00000000357 0.00000000227 0.000

lb/mmBtuO2 2.96E-13 3.74E-13 2.43E-13 0.000

ng/dscm 3.23E-04 4.05E-04 2.58E-04 0.000

ng/dscm@7%O2 3.43E-04 4.34E-04 2.81E-04 0.000

Location: Stack Platform - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run PJ4 R1 PJ4 R2 PJ4 R3

Elb/hr 3.02E+00 7.08E+00 2.03E+00 4.043

gr/dscf 2.40E-04 5.61E-04 1.60E-04 0.000

lb/mmBtuO2 5.28E-04 1.23E-03 3.49E-04 0.001

mg/dscm 5.50E-01 1.28E+00 3.67E-01 0.732

ppm 3.00E-01 7.00E-01 2.00E-01 0.400

ppm@7%O2 3.34E-01 7.75E-01 2.21E-01 0.443

Location: Stack Platform - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.97 0.99 0.9 0.953

Elb/hr 1.55E+00 1.58E+00 1.44E+00 1.523

lb/mmBtuO2 2.50E-04 2.55E-04 2.34E-04 0.000

mg/dscm 2.71E-01 2.80E-01 2.57E-01 0.269

mg/dscm@7%O2 2.90E-01 2.96E-01 2.71E-01 0.286

Compound: Hydrogen Fluoride

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.4 0.4 0.42 0.407

Elb/hr 6.39E-01 6.40E-01 6.72E-01 0.650

lb/mmBtuO2 1.03E-04 1.03E-04 1.09E-04 0.000

mg/dscm 1.12E-01 1.13E-01 1.20E-01 0.115

Monday, February 28, 2011 Page 13 of 33
6481_INTERMOUNTAIN

8/31/2010

mg/dscm@7%O2 1.20E-01 1.19E-01 1.27E-01 0.122

Location: Stack Platform - Method 29 

Compound: Antimony

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 1.184247 1.229485 1.20238 1.205

Elb/hr 9.43E-01 9.73E-01 9.47E-01 0.954

lb/mmBtuO2 1.60E-04 1.68E-04 1.62E-04 0.000

mg/dscm 1.73E-01 1.79E-01 1.72E-01 0.175

mg/dscm@7%O2 1.86E-01 1.95E-01 1.88E-01 0.190

Compound: Arsenic

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.02022 0.01888 0.01881 0.019

Elb/hr 1.61E-02 1.49E-02 1.48E-02 0.015

lb/mmBtuO2 2.74E-06 2.58E-06 2.53E-06 0.000

mg/dscm 2.95E-03 2.76E-03 2.69E-03 0.003

mg/dscm@7%O2 3.17E-03 3.00E-03 2.93E-03 0.003

Compound: Beryllium

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.00172 0.00119 0.00151 0.001

Elb/hr 1.37E-03 9.42E-04 1.19E-03 0.001

lb/mmBtuO2 2.33E-07 1.63E-07 2.03E-07 0.000

mg/dscm 2.51E-04 1.74E-04 2.16E-04 0.000

mg/dscm@7%O2 2.70E-04 1.89E-04 2.35E-04 0.000

Compound: Cadmium

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.001529 0.00125 0.001524 0.001

Elb/hr 1.22E-03 9.89E-04 1.20E-03 0.001

lb/mmBtuO2 2.07E-07 1.71E-07 2.05E-07 0.000

mg/dscm 2.23E-04 1.82E-04 2.18E-04 0.000

mg/dscm@7%O2 2.40E-04 1.98E-04 2.38E-04 0.000

Compound: Chromium

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.06523 0.05429 0.038052 0.053

Elb/hr 5.19E-02 4.30E-02 3.00E-02 0.042

lb/mmBtuO2 8.83E-06 7.43E-06 5.12E-06 0.000

mg/dscm 9.53E-03 7.92E-03 5.44E-03 0.008

mg/dscm@7%O2 1.02E-02 8.61E-03 5.93E-03 0.008

Compound: Filterable Particulate

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 241.5 241.9 226.3 236.567

Elb/hr 1.92E+02 1.91E+02 1.78E+02 187.000

Monday, February 28, 2011 Page 14 of 33
6481_INTERMOUNTAIN

8/31/2010

lb/mmBtuO2 3.27E-02 3.31E-02 3.04E-02 0.032

mg/dscm 3.53E+01 3.53E+01 3.24E+01 34.333

mg/dscm@7%O2 3.79E+01 3.84E+01 3.53E+01 37.200

Compound: Lead

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.029889 0.02882 0.029033 0.029

Elb/hr 2.38E-02 2.28E-02 2.29E-02 0.023

lb/mmBtuO2 4.05E-06 3.94E-06 3.90E-06 0.000

mg/dscm 4.37E-03 4.21E-03 4.15E-03 0.004

mg/dscm@7%O2 4.69E-03 4.58E-03 4.52E-03 0.005

Compound: Manganese

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.319968 0.29902 0.293857 0.304

Elb/hr 2.55E-01 2.37E-01 2.32E-01 0.241

lb/mmBtuO2 4.33E-05 4.09E-05 3.95E-05 0.000

mg/dscm 4.68E-02 4.36E-02 4.20E-02 0.044

mg/dscm@7%O2 5.03E-02 4.74E-02 4.58E-02 0.048

Compound: Nickel

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 4.30507 3.96703 4.16365 4.145

Elb/hr 3.43E+00 3.14E+00 3.28E+00 3.283

lb/mmBtuO2 5.83E-04 5.43E-04 5.60E-04 0.001

mg/dscm 6.29E-01 5.79E-01 5.95E-01 0.601

mg/dscm@7%O2 6.76E-01 6.29E-01 6.49E-01 0.651

Compound: Selenium

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 0.03101 0.03352 0.0344 0.033

Elb/hr 2.47E-02 2.65E-02 2.71E-02 0.026

lb/mmBtuO2 4.20E-06 4.59E-06 4.63E-06 0.000

mg/dscm 4.53E-03 4.89E-03 4.92E-03 0.005

mg/dscm@7%O2 4.87E-03 5.31E-03 5.36E-03 0.005

Location: Stack Platform - Method 6C

Compound: Sulfur Dioxide

Average

Run PJ4 R1 PJ4 R2 PJ4 R3

Elb/hr 3.93E+03 4.08E+03 4.09E+03 4,033.333

lb/mmBtuO2 6.34E-01 6.60E-01 6.66E-01 0.653

mg/dscm 6.87E+02 7.24E+02 7.31E+02 714.000

mg/dscm@7%O2 7.35E+02 7.65E+02 7.72E+02 757.333

ppm 2.58E+02 2.72E+02 2.75E+02 268.333

ppm@7%O2 2.76E+02 2.88E+02 2.90E+02 284.667

Location: Stack Platform - Method 7E

Monday, February 28, 2011 Page 15 of 33
6481_INTERMOUNTAIN

8/31/2010

Process Run Data

Compound: Nitrogen oxides (NOx)

Average

Run PJ4 R1 PJ4 R2 PJ4 R3

Elb/hr 1.45E+03 1.57E+03 1.42E+03 1,480.000

lb/mmBtuO2 2.34E-01 2.53E-01 2.32E-01 0.240

mg/dscm 2.54E+02 2.78E+02 2.55E+02 262.333

mg/dscm@7%O2 2.72E+02 2.94E+02 2.69E+02 278.333

ppm 1.33E+02 1.45E+02 1.33E+02 137.000

ppm@7%O2 1.42E+02 1.53E+02 1.40E+02 145.000

Location: Stack Platform - OTM - 27/28

Compound: Filterable PM2.5

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 29.6 35.4 39.9 34.967

lb/mmBtuO2 6.73E-03 8.04E-03 9.11E-03 0.008

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 110.9 66 104.6 93.833

lb/mmBtuO2 2.52E-02 1.50E-02 2.39E-02 0.021

Compound: Organic Condensible Particulate

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 2 1.8 0.7 1.500

lb/mmBtuO2 4.55E-04 4.09E-04 1.60E-04 0.000

Compound: Total PM2.5

Average

RunNumber PJ4 R1 PJ4 R2 PJ4 R3

Mass_mg 142.5 103.2 145.2 130.300

lb/mmBtuO2 3.24E-02 2.35E-02 3.32E-02 0.030

Monday, February 28, 2011 Page 16 of 33
6481_INTERMOUNTAIN

8/31/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Bituminous Coal Burned 8552.5 1000 Tons/hr 0

2 Bituminous Coal Burned 8552.5 1000 Tons/hr 0

3 Bituminous Coal Burned 8514.8 1000 Tons/hr 0

4 Bituminous Coal Burned 8471.5 1000 Tons/hr 0

1 Coal Feed Rate - 1SGA 381.54 ton/hr 0

2 Coal Feed Rate - 1SGA 381.54 ton/hr 0

3 Coal Feed Rate - 1SGA 383.69 ton/hr 0

4 Coal Feed Rate - 1SGA 381.27 ton/hr 0

1 Steam Pressure - 1SGA 2384.1 psi 0

2 Steam Pressure - 1SGA 2384.1 psi 0

3 Steam Pressure - 1SGA 2383.7 psi 0

4 Steam Pressure - 1SGA 2383.3 psi 0

1 Gross Electric Output - 1SGA 949.88 MWh 0

2 Gross Electric Output - 1SGA 950.01 MWh 0

3 Gross Electric Output - 1SGA 949.99 MWh 0

4 Gross Electric Output - 1SGA 949.9 MWh 0

1 Oxygen (O2) - 1SGA 3.33 % 0

2 Oxygen (O2) - 1SGA 3.3 % 0

3 Oxygen (O2) - 1SGA 3.45 % 0

4 Oxygen (O2) - 1SGA 3.16 % 0

1 Fuel Oil Feed Rate - 1SGA 0.02 klbh 0

2 Fuel Oil Feed Rate - 1SGA 0.03 klbh 0

3 Fuel Oil Feed Rate - 1SGA 0.03 klbh 0

4 Fuel Oil Feed Rate - 1SGA 0.03 klbh 0

1 Steam Flow Rate - 1SGA 6665.5 klbh 0

2 Steam Flow Rate - 1SGA 6684.5 klbh 0

3 Steam Flow Rate - 1SGA 6701.9 klbh 0

4 Steam Flow Rate - 1SGA 6706 klbh 0

1 Steam Temperature - 1SGA 1001.8 F 0

2 Steam Temperature - 1SGA 1002.5 F 0

3 Steam Temperature - 1SGA 1000.3 F 0

4 Steam Temperature - 1SGA 1001.6 F 0

2 Total Heat Input - 2SGA 8428.7 MMBtu/hr 0

Monday, February 28, 2011 Page 17 of 33
6481_INTERMOUNTAIN

8/31/2010

APCD Run Data

3 Total Heat Input - 2SGA 8467.0 MMBtu/hr 0

4 Total Heat Input - 2SGA 8474.5 MMBtu/hr 0

2 Steam Temperature - 2SGA 998.33 F 0

3 Steam Temperature - 2SGA 999.13 F 0

4 Steam Temperature - 2SGA 998.64 F 0

2 Steam Flow Rate - 2SGA 6503.1 klbh 0

3 Steam Flow Rate - 2SGA 6524.6 klbh 0

4 Steam Flow Rate - 2SGA 6513.5 klbh 0

2 Fuel Oil Feed Rate - 2SGA 0 klbh 0

3 Fuel Oil Feed Rate - 2SGA 0 klbh 0

4 Fuel Oil Feed Rate - 2SGA 0 klbh 0

2 Oxygen (O2) - 2SGA 3.29 % 0

3 Oxygen (O2) - 2SGA 3.5 % 0

4 Oxygen (O2) - 2SGA 3.45 % 0

2 Gross Electric Output - 2SGA 949.97 MWh 0

3 Gross Electric Output - 2SGA 950.08 MWh 0

4 Gross Electric Output - 2SGA 949.95 MWh 0

2 Steam Pressure - 2SGA 2357.7 psi 0

3 Steam Pressure - 2SGA 2356.5 psi 0

4 Steam Pressure - 2SGA 2358.4 psi 0

2 Coal Feed Rate -2SGA 381.96 ton/hr 0

3 Coal Feed Rate -2SGA 383.69 ton/hr 0

4 Coal Feed Rate -2SGA 384.04 ton/hr 0

1 Net Electric Output - 1SGA 895.85 MWh 0

2 Net Electric Output - 1SGA 895.38 MWh 0

3 Net Electric Output - 1SGA 896.29 MWh 0

4 Net Electric Output - 1SGA 895.86 MWh 0

2 Net Electric Output - 2SGA 888.77 MWh 0

3 Net Electric Output - 2SGA 888.59 MWh 0

4 Net Electric Output - 2SGA 889.5 MWh 0

Run Name Value UOM Comments

Target

Value

1 Scrubber Differential Pressure - Module B - 1SGA 1.81 inWC 0

2 Scrubber Differential Pressure - Module B - 1SGA 1.82 inWC 0

3 Scrubber Differential Pressure - Module B - 1SGA 1.86 inWC 0

Monday, February 28, 2011 Page 18 of 33
6481_INTERMOUNTAIN

8/31/2010

4 Scrubber Differential Pressure - Module B - 1SGA 1.83 inWC 0

1 Scrubber Differential Pressure - Module C - 1SGA 1.52 inWC 0

2 Scrubber Differential Pressure - Module C - 1SGA 1.52 inWC 0

3 Scrubber Differential Pressure - Module C - 1SGA 1.55 inWC 0

4 Scrubber Differential Pressure - Module C - 1SGA 1.55 inWC 0

1 Scrubber Differential Pressure - Module D - 1SGA 1.61 inWC 0

2 Scrubber Differential Pressure - Module D - 1SGA 1.61 inWC 0

3 Scrubber Differential Pressure - Module D - 1SGA 1.58 inWC 0

4 Scrubber Differential Pressure - Module D - 1SGA 1.55 inWC 0

1 Scrubber Differential Pressure - Module E - 1SGA 2.03 inWC 0

2 Scrubber Differential Pressure - Module E - 1SGA 2.05 inWC 0

3 Scrubber Differential Pressure - Module E - 1SGA 2.06 inWC 0

4 Scrubber Differential Pressure - Module E - 1SGA 2.01 inWC 0

1 Fabric Filter Differential Pressure - A Casing - 

1SGA

9.08 inWC 0

2 Fabric Filter Differential Pressure - A Casing - 

1SGA

9.23 inWC 0

3 Fabric Filter Differential Pressure - A Casing - 

1SGA

9.28 inWC 0

4 Fabric Filter Differential Pressure - A Casing - 

1SGA

9.2 inWC 0

1 Fabric Filter Differential Pressure - B Casing - 

1SGA

8.58 inWC 0

2 Fabric Filter Differential Pressure - B Casing - 

1SGA

8.78 inWC 0

3 Fabric Filter Differential Pressure - B Casing - 

1SGA

8.88 inWC 0

4 Fabric Filter Differential Pressure - B Casing - 

1SGA

8.75 inWC 0

1 Fabric Filter Differential Pressure - C Casing - 

1SGA

8 inWC 0

2 Fabric Filter Differential Pressure - C Casing - 

1SGA

8.15 inWC 0

3 Fabric Filter Differential Pressure - C Casing - 

1SGA

8.19 inWC 0

4 Fabric Filter Differential Pressure - C Casing - 

1SGA

8.12 inWC 0

1 Average Scrubber Differential Pressure - 1SGA 1.74 inWC 0

2 Average Scrubber Differential Pressure - 1SGA 1.75 inWC 0

3 Average Scrubber Differential Pressure - 1SGA 1.76 inWC 0

4 Average Scrubber Differential Pressure - 1SGA 1.73 inWC 0

Monday, February 28, 2011 Page 19 of 33
6481_INTERMOUNTAIN

8/31/2010

1 Average Fabric Filter Differential Pressure - 1SGA 8.55 inWC 0

2 Average Fabric Filter Differential Pressure - 1SGA 8.72 inWC 0

3 Average Fabric Filter Differential Pressure - 1SGA 8.78 inWC 0

4 Average Fabric Filter Differential Pressure - 1SGA 8.69 inWC 0

1 Scrubber pH Module B - 1SGA 5.71 pH 0

2 Scrubber pH Module B - 1SGA 5.71 pH 0

3 Scrubber pH Module B - 1SGA 5.72 pH 0

4 Scrubber pH Module B - 1SGA 5.72 pH 0

1 Scrubber pH Module C - 1SGA 5.74 pH 0

2 Scrubber pH Module C - 1SGA 5.76 pH 0

3 Scrubber pH Module C - 1SGA 5.78 pH 0

4 Scrubber pH Module C - 1SGA 5.8 pH 0

1 Scrubber pH Module D - 1SGA 5.75 pH 0

2 Scrubber pH Module D - 1SGA 5.73 pH 0

3 Scrubber pH Module D - 1SGA 5.72 pH 0

4 Scrubber pH Module D - 1SGA 5.75 pH 0

1 Scrubber pH Module E - 1SGA 5.7 pH 0

2 Scrubber pH Module E - 1SGA 5.66 pH 0

3 Scrubber pH Module E - 1SGA 6 pH 0

4 Scrubber pH Module E - 1SGA 5.88 pH 0

1 Average Scrubber pH - 1SGA 5.72 pH 0

2 Average Scrubber pH - 1SGA 5.72 pH 0

3 Average Scrubber pH - 1SGA 5.8 pH 0

4 Average Scrubber pH - 1SGA 5.79 pH 0

1 Scrubber Slurry Feed Rate Module B - 1SGA 19.5 gpm 0

2 Scrubber Slurry Feed Rate Module B - 1SGA 19.5 gpm 0

3 Scrubber Slurry Feed Rate Module B - 1SGA 19.92 gpm 0

4 Scrubber Slurry Feed Rate Module B - 1SGA 19 gpm 0

1 Scrubber Slurry Feed Rate Module C - 1SGA 24.56 gpm 0

2 Scrubber Slurry Feed Rate Module C - 1SGA 24.56 gpm 0

3 Scrubber Slurry Feed Rate Module C - 1SGA 19.4 gpm 0

4 Scrubber Slurry Feed Rate Module C - 1SGA 19.34 gpm 0

1 Scrubber Slurry Feed Rate Module D - 1SGA 21.59 gpm 0

2 Scrubber Slurry Feed Rate Module D - 1SGA 21.59 gpm 0

3 Scrubber Slurry Feed Rate Module D - 1SGA 21.03 gpm 0

4 Scrubber Slurry Feed Rate Module D - 1SGA 20.21 gpm 0

Monday, February 28, 2011 Page 20 of 33
6481_INTERMOUNTAIN

8/31/2010

1 Scrubber Slurry Feed Rate Module E - 1SGA 63.06 gpm 0

2 Scrubber Slurry Feed Rate Module E - 1SGA 63.06 gpm 0

3 Scrubber Slurry Feed Rate Module E - 1SGA 78.19 gpm 0

4 Scrubber Slurry Feed Rate Module E - 1SGA 18.33 gpm 0

1 Scrubber Limestone Feed Rate - 1SGA 24501 lb/hr 0

2 Scrubber Limestone Feed Rate - 1SGA 24257 lb/hr 0

3 Scrubber Limestone Feed Rate - 1SGA 26224 lb/hr 0

4 Scrubber Limestone Feed Rate - 1SGA 14358 lb/hr 0

1 Scrubber Slurry Density - 1SGA 31.73 % 0

2 Scrubber Slurry Density - 1SGA 31.77 % 0

3 Scrubber Slurry Density - 1SGA 31.52 % 0

4 Scrubber Slurry Density - 1SGA 31.09 % 0

1 Total Spray Flow Rate - 1SGA 178752 gpm 0

2 Total Spray Flow Rate - 1SGA 178726 gpm 0

3 Total Spray Flow Rate - 1SGA 178684 gpm 0

4 Total Spray Flow Rate - 1SGA 178623 gpm 0

1 B Module HP Spray Amps - 1SGA 27.35 ohms 0

2 B Module HP Spray Amps - 1SGA 27.34 ohms 0

3 B Module HP Spray Amps - 1SGA 27.32 ohms 0

4 B Module HP Spray Amps - 1SGA 27.3 ohms 0

1 B Module IP Spray Amps - 1SGA 24.08 ohms 0

2 B Module IP Spray Amps - 1SGA 24.13 ohms 0

3 B Module IP Spray Amps - 1SGA 24.21 ohms 0

4 B Module IP Spray Amps - 1SGA 24.27 ohms 0

1 B Modulr LP Spray Amps - 1SGA 24.4 ohms 0

2 B Modulr LP Spray Amps - 1SGA 24.4 ohms 0

3 B Modulr LP Spray Amps - 1SGA 24.39 ohms 0

4 B Modulr LP Spray Amps - 1SGA 24.46 ohms 0

1 C Module HP Spray Amps - 1SGA 24.93 ohms 0

2 C Module HP Spray Amps - 1SGA 24.86 ohms 0

3 C Module HP Spray Amps - 1SGA 24.77 ohms 0

4 C Module HP Spray Amps - 1SGA 24.85 ohms 0

1 C Module IP Spray Amps - 1SGA 23.03 ohms 0

2 C Module IP Spray Amps - 1SGA 22.94 ohms 0

3 C Module IP Spray Amps - 1SGA 22.89 ohms 0

4 C Module IP Spray Amps - 1SGA 22.85 ohms 0

Monday, February 28, 2011 Page 21 of 33
6481_INTERMOUNTAIN

8/31/2010

Process Lab Run Data

1 C Module LP Spray Amps - 1SGA 23.04 ohms 0

2 C Module LP Spray Amps - 1SGA 22.99 ohms 0

3 C Module LP Spray Amps - 1SGA 22.99 ohms 0

4 C Module LP Spray Amps - 1SGA 23.08 ohms 0

1 D Module HP Spray Amps - 1SGA 25.66 ohms 0

2 D Module HP Spray Amps - 1SGA 25.64 ohms 0

3 D Module HP Spray Amps - 1SGA 25.5 ohms 0

4 D Module HP Spray Amps - 1SGA 25.41 ohms 0

1 D Module IP Spray Amps - 1SGA 25.79 ohms 0

2 D Module IP Spray Amps - 1SGA 25.8 ohms 0

3 D Module IP Spray Amps - 1SGA 25.8 ohms 0

4 D Module IP Spray Amps - 1SGA 25.8 ohms 0

1 D Module LP Spray Amps - 1SGA 24.54 ohms 0

2 D Module LP Spray Amps - 1SGA 24.61 ohms 0

3 D Module LP Spray Amps - 1SGA 24.73 ohms 0

4 D Module LP Spray Amps - 1SGA 24.56 ohms 0

1 E Module HP Spray Amps - 1SGA 25.86 ohms 0

2 E Module HP Spray Amps - 1SGA 25.96 ohms 0

3 E Module HP Spray Amps - 1SGA 26.08 ohms 0

4 E Module HP Spray Amps - 1SGA 26.09 ohms 0

1 E Module IP Spray Amps - 1SGA 24.27 ohms 0

2 E Module IP Spray Amps - 1SGA 24.23 ohms 0

3 E Module IP Spray Amps - 1SGA 24.18 ohms 0

4 E Module IP Spray Amps - 1SGA 24.14 ohms 0

1 E Module LP Spray Amps - 1SGA 23.46 ohms 0

2 E Module LP Spray Amps - 1SGA 23.46 ohms 0

3 E Module LP Spray Amps - 1SGA 23.43 ohms 0

4 E Module LP Spray Amps - 1SGA 23.36 ohms 0

Run Name Value UOM Comments

1 Formaldehyde (Gas Stream) - 1SGA 10.8 ug

2 Formaldehyde (Gas Stream) - 1SGA 9.39 ug

3 Formaldehyde (Gas Stream) - 1SGA 9.1 ug

4 Formaldehyde (Gas Stream) - 1SGA 9.36 ug

1 Higher Heating Value (Fuel) - 1SGA 11202 Btu/lb

2 Higher Heating Value (Fuel) - 1SGA 11216 Btu/lb

Monday, February 28, 2011 Page 22 of 33
6481_INTERMOUNTAIN

8/31/2010

3 Higher Heating Value (Fuel) - 1SGA 11085 Btu/lb

4 Higher Heating Value (Fuel) - 1SGA 11231 Btu/lb

1 Moisture (Fuel) - 1SGA 8.85 %

2 Moisture (Fuel) - 1SGA 8.72 %

3 Moisture (Fuel) - 1SGA 8.34 %

4 Moisture (Fuel) - 1SGA 7.44 %

1 Residule Moisture (Fuel) - 1SGA

Moisture (Fuel) - 1SGA

1.99 %

2 Residule Moisture (Fuel) - 1SGA

Moisture (Fuel) - 1SGA

2.02 %

3 Residule Moisture (Fuel) - 1SGA

Moisture (Fuel) - 1SGA

2 %

4 Residule Moisture (Fuel) - 1SGA

Moisture (Fuel) - 1SGA

2.24 %

1 Ash Proximate (Fuel) - 1SGA 12.72 %

2 Ash Proximate (Fuel) - 1SGA 12.82 %

3 Ash Proximate (Fuel) - 1SGA 13.84 %

4 Ash Proximate (Fuel) - 1SGA 13.84 %

1 Volatiles Proximate (Fuel) - 1SGA 37.36 %

2 Volatiles Proximate (Fuel) - 1SGA 37.52 %

3 Volatiles Proximate (Fuel) - 1SGA 36.76 %

4 Volatiles Proximate (Fuel) - 1SGA 37.65 %

1 Fixed Carbon (Fuel) - 1SGA 45.06 %

2 Fixed Carbon (Fuel) - 1SGA 44.85 %

3 Fixed Carbon (Fuel) - 1SGA 44.8 %

4 Fixed Carbon (Fuel) - 1SGA 44.37 %

1 Carbon Ultimate (Fuel) - 1SGA 68.82 %

2 Carbon Ultimate (Fuel) - 1SGA 68.81 %

3 Carbon Ultimate (Fuel) - 1SGA 67.91 %

4 Carbon Ultimate (Fuel) - 1SGA 67.77 %

1 Hydrogen Ultimate (Fuel) - 1SGA 4.88 %

2 Hydrogen Ultimate (Fuel) - 1SGA 4.93 %

3 Hydrogen Ultimate (Fuel) - 1SGA 4.85 %

4 Hydrogen Ultimate (Fuel) - 1SGA 4.83 %

1 Nitrogent Ultimate (Fuel) - 1SGA 1.44 %

2 Nitrogent Ultimate (Fuel) - 1SGA 1.48 %

3 Nitrogent Ultimate (Fuel) - 1SGA 1.44 %

4 Nitrogent Ultimate (Fuel) - 1SGA 1.44 %

1 Methane Content (Gas Stream) - 1SGA 2.2 ppm

2 Methane Content (Gas Stream) - 1SGA 2.3 ppm

3 Methane Content (Gas Stream) - 1SGA 2.2 ppm

4 Methane Content (Gas Stream) - 1SGA 2.2 ppm

1 Formaldehyde (Gas Stream) - 2SGA 9.8 ug

2 Formaldehyde (Gas Stream) - 2SGA 9.44 ug

3 Formaldehyde (Gas Stream) - 2SGA 23.1 ug

Monday, February 28, 2011 Page 23 of 33
6481_INTERMOUNTAIN

8/31/2010

4 Formaldehyde (Gas Stream) - 2SGA 0 ug

1 Higher Heating Value (Fuel) - 2SGA 11196 Btu/lb

2 Higher Heating Value (Fuel) - 2SGA 11397 Btu/lb

3 Higher Heating Value (Fuel) - 2SGA 11514 Btu/lb

4 Higher Heating Value (Fuel) - 2SGA 11592 Btu/lb

1 Moisture (Fuel) - 2SGA 8 %

2 Moisture (Fuel) - 2SGA 6.62 %

3 Moisture (Fuel) - 2SGA 5.82 %

4 Moisture (Fuel) - 2SGA 6.19 %

1 Residule Moisture (Fuel) - 2SGA 1.88 %

2 Residule Moisture (Fuel) - 2SGA 1.52 %

3 Residule Moisture (Fuel) - 2SGA 1.28 %

4 Residule Moisture (Fuel) - 2SGA 1.4 %

1 Ash Proximate (Fuel) - 2SGA 13.62 %

2 Ash Proximate (Fuel) - 2SGA 14.73 %

3 Ash Proximate (Fuel) - 2SGA 15.24 %

4 Ash Proximate (Fuel) - 2SGA 14.49 %

1 Volatiles Proximate (Fuel) - 2SGA 37.46 %

2 Volatiles Proximate (Fuel) - 2SGA 36.64 %

3 Volatiles Proximate (Fuel) - 2SGA 36.35 %

4 Volatiles Proximate (Fuel) - 2SGA 36.52 %

1 Fixed Carbon (Fuel) - 2SGA 44.48 %

2 Fixed Carbon (Fuel) - 2SGA 44.99 %

3 Fixed Carbon (Fuel) - 2SGA 45.22 %

4 Fixed Carbon (Fuel) - 2SGA 45.62 %

1 Carbon Ultimate (Fuel) - 2SGA 67.87 %

2 Carbon Ultimate (Fuel) - 2SGA 67.88 %

3 Carbon Ultimate (Fuel) - 2SGA 68.09 %

4 Carbon Ultimate (Fuel) - 2SGA 68.95 %

1 Hydrogen Ultimate (Fuel) - 2SGA 4.85 %

2 Hydrogen Ultimate (Fuel) - 2SGA 4.8 %

3 Hydrogen Ultimate (Fuel) - 2SGA 4.8 %

4 Hydrogen Ultimate (Fuel) - 2SGA 4.99 %

1 Nitrogent Ultimate (Fuel) - 2SGA 1.45 %

2 Nitrogent Ultimate (Fuel) - 2SGA 1.52 %

3 Nitrogent Ultimate (Fuel) - 2SGA 1.57 %

4 Nitrogent Ultimate (Fuel) - 2SGA 1.58 %

1 Methane Content (Gas Stream) - 2SGA 2.5 ppm

2 Methane Content (Gas Stream) - 2SGA 2.5 ppm

3 Methane Content (Gas Stream) - 2SGA 2.5 ppm

4 Methane Content (Gas Stream) - 2SGA 0 ppm

Monday, February 28, 2011 Page 24 of 33
6481_INTERMOUNTAIN

8/31/2010

Sampling / Stack Data Results Detail

Location 1SGA - EPA Method 316

Average

Run Number M316-4 M316-1 M316-2

Test Date 6/15/2010 6/15/2010 6/15/2010

Run Start Time 4:05:00 PM 8:13:00 AM 10:40:00 AM

Run Finish Time 5:55:00 PM 10:03:00 AM 12:30:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 120 120 120

Nozzle Diameter, inches 0.18 0.18 0.18 0.180

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.0033 1.0033 1.0033 1.003

Barometric Pressure, inches of Mercury 24.86 24.86 24.86 24.860

Average Orifice Meter Differential, inches H2O 1.45 1.63 1.56 1.547

Dry Gas Meter Volume Sampled, cubic feet 84.329 90.060 88.207 87.532

Average Dry Gas Meter Temperature, °F 88.71 80.46 82.75 83.973

Dry Gas Meter Volume Sampled, dscf 67.936 73.699 71.863 71.166

Total Moisture Liquid collected, g 257.5 263.9 257 259.467

Volume of Water Vapor, standard cubic feet 12.12 12.42 12.10 12.213

Moisture Content of Stack Gas, % 15.14 14.42 14.41 14.657

Moisture Saturation at Stack Gas Temperature, % 14.94 14.91 15.11 14.987

Dry Mole Fraction 0.8506 0.8558 0.8559 0.854

Carbon Dioxide, % 13.61 13.89 13.89 13.797

Oxygen, % 5.61 5.59 5.6 5.600

Carbon Monoxide & Nitrogen, % 80.78 80.52 80.51 80.603

Fuel Factor 1.12 1.10 1.10

Dry Molecular Weight, lb/lb-Mole 30.40 30.45 30.45 30.433

Wet Molecular weight, lb/lb-Mole 28.58 28.65 28.66 28.630

Flue Gas Static Pressure, inches of H2O -0.95 -0.95 -0.95 -0.950

Absolute Flue Gas Pressure, inches of Mercury 24.79 24.79 24.79 24.790

Average Stack Gas Temperature, °F 122.67 122.58 123.08 122.777

Average Velocity Head, inches of H2O 1.5699139437

7914

1.757410451

26146

1.696863238

15571

1.675

Average Stack Gas Velocity, feet/second 81.60 86.22 84.74 84.187

Stack Cross-Sectional Area, square feet 615.752 615.752 615.752 615.752

Dry Volumetric Flow Rate, dry scfm 1,925,301.8 2,047,060.5 2,010,431.5 1,994,264.6

00

Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,014,721.8 3,185,408.2 3,130,729.5 3,110,286.5

00

Percent Isokinetic of Sampling Rate, % 102.5 104.5 103.8 103.600

Percent Excess Air, % 35.7 35.7 35.8 35.733

F-Factor, dscfm/MMBtu @ %O2 9658 9681 9703 9,680.667

Round Duct Diameter, inches 336 336 336

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10565 10613 10641 10,606.333

Fc 0 0 0 0.000

Monday, February 28, 2011 Page 25 of 33
6481_INTERMOUNTAIN

8/31/2010

Location 1SGA - EPA Method 316 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 28, 2011 Page 26 of 33
6481_INTERMOUNTAIN

8/31/2010

Location 1SGA - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, % Method 10 Method 10 Method 10

Oxygen, % 6/15/2010 6/15/2010 6/15/2010

Fuel Factor 0.43 0.15 0.02

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2 CC249349-CO CC249349-

CO

CC249349-

CO

Moisture, %

Analyzer Make 10:14:00 AM 12:50:00 PM 3:21:00 PM

Analyzer Model 2403905 2351467 2186012 2,313,794.6

67

Analyzer Serial Number M316 - Run 1 M316 - Run 

2

M316 - Run 3

Operating Range 14.43 14.41 15.6 14.813

Operating Units M316 - Run 1 M316 - Run 

2

M316 - Run 3

No. Readings/Avg. 13.89 13.89 13.83 13.870

Calibration Set 5.59 5.6 5.65 5.613

Calibration Pre Zero Cylinder ID M3A - Run 1 M3A - Run 2 M3A - Run 3

Calibration Pre Zero Cylinder Instrument Response Servomex Servomex Servomex

Calibration Pre Zero Cylinder Bias 4900 4900 4900 4,900.000

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID 500 500 500

Calibration Pre High Cylinder Instrument Response ppm ppm ppm

Calibration Pre High Cylinder Bias 60 60 60 60.000

Calibration Pre High Cylinder Drift 1 1 1 1.000

Calibration Post Zero Cylinder ID 1 1 1

Calibration Post Zero Cylinder Instrument Response Zero Gas Zero Gas Zero Gas

Calibration Post Zero Cylinder Bias -0.1 -0.36 -0.33 -0.263

Calibration Post Zero Cylinder Drift 0.1 -0.04 -0.02 0.013

Calibration Post High Cylinder ID 0 0 0

Calibration Post High Cylinder Instrument Response CC249349-CO CC249349-

CO

CC249349-

CO

Calibration Post High Cylinder Bias 99.68 98.83 98.53 99.013

Calibration Post High Cylinder Drift -1.54 -1.97 -2.12 -1.877

Cavg 0 0 0 0.000

Cavg Units Zero Gas Zero Gas Zero Gas

Cgas -0.36 -0.33 -0.55 -0.413

Cgas Units -0.04 -0.02 -0.13

Fuel Type 0.14 0.02 0.11

Fw 98.83 98.53 98.5 98.620

Fc -1.97 -2.12 -2.14 -2.077

Cgasw 130.85 155.58 189.09 158.507

Cgasw Units ppmvd ppmvd ppmvd

Monday, February 28, 2011 Page 27 of 33
6481_INTERMOUNTAIN

8/31/2010

Location 1SGA - Method 25A

Average

Run Number 1 2 3

Test Date 6/15/2010 6/15/2010 6/15/2010

Run Start Time 8:05:00 AM 10:51:00 AM 1:22:00 PM

Run Finish Time 10:14:00 AM 12:50:00 PM 3:21:00 PM

Carbon Dioxide, % 13.89 13.89 13.83 13.870

Oxygen, % 5.59 5.6 5.65 5.613

Fuel Factor 1.1 1.1 1.1

Dry Volumetric Flow Rate, dry scfm 2403905 2351467 2186012 2,313,794.6

67

F-Factor, dscfm/MMBtu @ %O2 9681 9703 9719 9,701.000

Moisture, % 14.43 14.41 15.6 14.813

Analyzer Make Vig VIG VIG

Analyzer Model 20/2 20/2 20/2

Analyzer Serial Number

Operating Range 10 10 10 10.000

Operating Units ppm ppm ppm

No. Readings/Avg. 60 60 60 60.000

Calibration Set 2 2 2 2.000

Calibration Pre Zero Cylinder ID Zero Gas Zero Gas Zero Gas

Calibration Pre Zero Cylinder Instrument Response 0.11 0.06 0.14 0.103

Calibration Pre Zero Cylinder Bias 0 -0.5 0.3 -0.067

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC150368-

THC

CC150368-

THC

CC150368-

THC

Calibration Pre High Cylinder Instrument Response 4.1 3.98 4.06 4.047

Calibration Pre High Cylinder Bias 0 -1.2 -0.4 -0.533

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Zero Gas Zero Gas Zero Gas

Calibration Post Zero Cylinder Instrument Response 0.06 0.14 0.28 0.160

Calibration Post Zero Cylinder Bias -0.5 0.3 1.7 0.500

Calibration Post Zero Cylinder Drift 0.5 0.8 1.4 0.900

Calibration Post High Cylinder ID CC150368-

THC

CC150368-

THC

CC150368-

THC

Calibration Post High Cylinder Instrument Response 3.98 4.06 4.07 4.037

Calibration Post High Cylinder Bias -1.2 -0.4 -0.3 -0.633

Calibration Post High Cylinder Drift 1.2 0.8 0.1 0.700

Cavg 6.3 3.12 1.72 3.713

Cavg Units ppmvw ppmvw ppmvw

Cgas 7.4192 3.6365 1.875 4.310

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 10613 10641 10652 10,635.333

Fc 0 0 0 0.000

Cgasw 6.3485714285

7143

3.112448979

59184

1.582464332

03632

3.681

Cgasw Units ppmvw ppmvw ppmvw

Monday, February 28, 2011 Page 28 of 33
6481_INTERMOUNTAIN

8/31/2010

Location 1SGA - Method 25A 3

Average

Run Number 4

Test Date 6/15/2010

Run Start Time 4:01:00 PM

Run Finish Time 6:00:00 PM

Carbon Dioxide, % 14.13 14.130

Oxygen, % 5.29 5.290

Fuel Factor 1.1

Dry Volumetric Flow Rate, dry scfm 2264127 2,264,127.0

00

F-Factor, dscfm/MMBtu @ %O2 9658 9,658.000

Moisture, % 14.06 14.060

Analyzer Make VIG

Analyzer Model 20/2

Analyzer Serial Number

Operating Range 10 10.000

Operating Units ppm

No. Readings/Avg. 60 60.000

Calibration Set 2 2.000

Calibration Pre Zero Cylinder ID Zero Gas

Calibration Pre Zero Cylinder Instrument Response 0.28 0.280

Calibration Pre Zero Cylinder Bias 1.7 1.700

Calibration Pre Zero Cylinder Drift 0 0.000

Calibration Pre High Cylinder ID CC150368-

THC

Calibration Pre High Cylinder Instrument Response 4.07 4.070

Calibration Pre High Cylinder Bias -0.3 -0.300

Calibration Pre High Cylinder Drift 0 0.000

Calibration Post Zero Cylinder ID Zero Gas

Calibration Post Zero Cylinder Instrument Response 0.28 0.280

Calibration Post Zero Cylinder Bias 1.7 1.700

Calibration Post Zero Cylinder Drift 0 0.000

Calibration Post High Cylinder ID CC150368-

THC

Calibration Post High Cylinder Instrument Response 4.07 4.070

Calibration Post High Cylinder Bias -0.3 -0.300

Calibration Post High Cylinder Drift 0 0.000

Cavg 1.59 1.590

Cavg Units ppmvw

Cgas 1.6249 1.625

Cgas Units ppmvd

Fuel Type Override

Fw 10565 10,565.000

Fc 0 0.000

Cgasw 1.3964116094

9868

1.396

Cgasw Units ppmvw

Monday, February 28, 2011 Page 29 of 33
6481_INTERMOUNTAIN

8/31/2010

Location 1SGA - Method 3A CO2

Average

Run Number 1 2 3

Test Date 6/15/2010 6/15/2010 6/15/2010

Run Start Time 8:05:00 AM 10:51:00 AM 1:22:00 PM

Run Finish Time 10:14:00 AM 12:50:00 PM 3:21:00 PM

Carbon Dioxide, % 13.89 13.89 13.83 13.870

Oxygen, % 5.59 5.6 5.65 5.613

Fuel Factor 1.1 1.1 1.1

Dry Volumetric Flow Rate, dry scfm 2403905 2351467 2186012 2,313,794.6

67

F-Factor, dscfm/MMBtu @ %O2 9681 9703 9719 9,701.000

Moisture, % 14.43 14.41 15.6 14.813

Analyzer Make Servomex Servomex Servomex

Analyzer Model 4900 4900 4900 4,900.000

Analyzer Serial Number

Operating Range 25 25 25 25.000

Operating Units % % %

No. Readings/Avg. 60 60 60 60.000

Calibration Set 3 3 3 3.000

Calibration Pre Zero Cylinder ID Zero Gas Zero Gas Zero Gas

Calibration Pre Zero Cylinder Instrument Response -0.04 0.04 0.1 0.033

Calibration Pre Zero Cylinder Bias 0.04 0.36 0.6 0.333

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC155303-

CO2

CC155303-

CO2

CC155303-

CO2

Calibration Pre High Cylinder Instrument Response 11.87 11.86 11.8 11.843

Calibration Pre High Cylinder Bias -0.76 -0.8 -1.04 -0.867

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Zero Gas Zero Gas Zero Gas

Calibration Post Zero Cylinder Instrument Response 0.04 0.1 0.1 0.080

Calibration Post Zero Cylinder Bias 0.36 0.6 0.6 0.520

Calibration Post Zero Cylinder Drift 0.32 0.24 0 0.187

Calibration Post High Cylinder ID CC155303-

CO2

CC155303-

CO2

CC155303-

CO2

Calibration Post High Cylinder Instrument Response 11.86 11.8 11.76 11.807

Calibration Post High Cylinder Bias -0.8 -1.04 -1.2 -1.013

Calibration Post High Cylinder Drift 0.04 0.24 0.16 0.147

Cavg 13.5 13.46 13.34 13.433

Cavg Units %vd %vd %vd

Cgas 13.8812 13.891 13.8295 13.867

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw 10613 10641 10652 10,635.333

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Monday, February 28, 2011 Page 30 of 33
6481_INTERMOUNTAIN

8/31/2010

Location 1SGA - Method 3A CO2 3

Average

Run Number 4

Test Date 6/15/2010

Run Start Time 4:01:00 PM

Run Finish Time 6:00:00 PM

Carbon Dioxide, % 14.13 14.130

Oxygen, % 5.29 5.290

Fuel Factor 1.1

Dry Volumetric Flow Rate, dry scfm 2264127 2,264,127.0

00

F-Factor, dscfm/MMBtu @ %O2 9658 9,658.000

Moisture, % 14.06 14.060

Analyzer Make Servomex

Analyzer Model 4900 4,900.000

Analyzer Serial Number

Operating Range 25 25.000

Operating Units %

No. Readings/Avg. 60 60.000

Calibration Set 3 3.000

Calibration Pre Zero Cylinder ID Zero Gas

Calibration Pre Zero Cylinder Instrument Response 0.1 0.100

Calibration Pre Zero Cylinder Bias 0.6 0.600

Calibration Pre Zero Cylinder Drift 0 0.000

Calibration Pre High Cylinder ID CC155303-

CO2

Calibration Pre High Cylinder Instrument Response 11.76 11.760

Calibration Pre High Cylinder Bias -1.2 -1.200

Calibration Pre High Cylinder Drift 0 0.000

Calibration Post Zero Cylinder ID Zero Gas

Calibration Post Zero Cylinder Instrument Response 0.08 0.080

Calibration Post Zero Cylinder Bias 0.52 0.520

Calibration Post Zero Cylinder Drift 0.08 0.080

Calibration Post High Cylinder ID CC155303-

CO2

Calibration Post High Cylinder Instrument Response 11.77 11.770

Calibration Post High Cylinder Bias -1.16 -1.160

Calibration Post High Cylinder Drift 0.04 0.040

Cavg 13.61 13.610

Cavg Units %vd

Cgas 14.128 14.128

Cgas Units %vd

Fuel Type Override

Fw 10565 10,565.000

Fc 0 0.000

Cgasw 0 0.000

Cgasw Units

Monday, February 28, 2011 Page 31 of 33
6481_INTERMOUNTAIN

8/31/2010

Location 1SGA - Method 3A O2

Average

Run Number 1 2 3

Test Date 6/15/2010 6/15/2010 6/15/2010

Run Start Time 8:05:00 AM 10:51:00 AM 1:22:00 PM

Run Finish Time 10:14:00 AM 12:50:00 PM 3:21:00 PM

Carbon Dioxide, % 13.89 13.89 13.83 13.870

Oxygen, % 5.59 5.6 5.65 5.613

Fuel Factor 1.1 1.1 1.1

Dry Volumetric Flow Rate, dry scfm 2403905 2351467 2186012 2,313,794.6

67

F-Factor, dscfm/MMBtu @ %O2 9681 9703 9719 9,701.000

Moisture, % 14.43 14.41 15.6 14.813

Analyzer Make Servomex Servomex Servomex

Analyzer Model 4900 4900 4900 4,900.000

Analyzer Serial Number

Operating Range 25 25 25 25.000

Operating Units % % %

No. Readings/Avg. 60 60 60 60.000

Calibration Set 7 7 7 7.000

Calibration Pre Zero Cylinder ID Zero Gas Zero Gas Zero Gas

Calibration Pre Zero Cylinder Instrument Response 0.07 0.16 0.3 0.177

Calibration Pre Zero Cylinder Bias 0.16 0.52 1.08 0.587

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC155303-O2 CC155303-

O2

CC155303-

O2

Calibration Pre High Cylinder Instrument Response 11.97 12 12.11 12.027

Calibration Pre High Cylinder Bias -0.6 -0.48 -0.04 -0.373

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Zero Gas Zero Gas Zero Gas

Calibration Post Zero Cylinder Instrument Response 0.16 0.3 0.42 0.293

Calibration Post Zero Cylinder Bias 0.52 1.08 1.56 1.053

Calibration Post Zero Cylinder Drift 0.36 0.56 0.48 0.467

Calibration Post High Cylinder ID CC155303-O2 CC155303-

O2

CC155303-

O2

Calibration Post High Cylinder Instrument Response 12 12.11 12.18 12.097

Calibration Post High Cylinder Bias -0.48 -0.04 0.24 -0.093

Calibration Post High Cylinder Drift 0.12 0.44 0.28 0.280

Cavg 5.6 5.71 5.87 5.727

Cavg Units %vd %vd %vd

Cgas 5.5913 5.6074 5.6573 5.619

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw 10613 10641 10652 10,635.333

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Monday, February 28, 2011 Page 32 of 33
6481_INTERMOUNTAIN

8/31/2010

Location 1SGA - Method 3A O2 3

Average

Run Number 4

Test Date 6/15/2010

Run Start Time 4:01:00 PM

Run Finish Time 6:00:00 PM

Carbon Dioxide, % 14.13 14.130

Oxygen, % 5.29 5.290

Fuel Factor 1.1

Dry Volumetric Flow Rate, dry scfm 2264127 2,264,127.0

00

F-Factor, dscfm/MMBtu @ %O2 9658 9,658.000

Moisture, % 14.06 14.060

Analyzer Make Servomex

Analyzer Model 4900 4,900.000

Analyzer Serial Number

Operating Range 0.25 0.250

Operating Units %

No. Readings/Avg. 60 60.000

Calibration Set 7 7.000

Calibration Pre Zero Cylinder ID Zero Gas

Calibration Pre Zero Cylinder Instrument Response 0.42 0.420

Calibration Pre Zero Cylinder Bias 1.56 1.560

Calibration Pre Zero Cylinder Drift 0 0.000

Calibration Pre High Cylinder ID CC155303-O2

Calibration Pre High Cylinder Instrument Response 12.18 12.180

Calibration Pre High Cylinder Bias 0.24 0.240

Calibration Pre High Cylinder Drift 0 0.000

Calibration Post Zero Cylinder ID Zero Gas

Calibration Post Zero Cylinder Instrument Response 0.54 0.540

Calibration Post Zero Cylinder Bias 2.04 2.040

Calibration Post Zero Cylinder Drift 0.48 0.480

Calibration Post High Cylinder ID CC155303-O2

Calibration Post High Cylinder Instrument Response 12.23 12.230

Calibration Post High Cylinder Bias 0.44 0.440

Calibration Post High Cylinder Drift 0.2 0.200

Cavg 5.61 5.610

Cavg Units %vd

Cgas 5.2941 5.294

Cgas Units %vd

Fuel Type Override

Fw 10565 10,565.000

Fc 0 0.000

Cgasw 0 0.000

Cgasw Units

Monday, February 28, 2011 Page 33 of 33