Facility _Information

facility _id utility

_code legal_owner_name

legl_operator_name

legal_address_type

legal_address

legal_city legal_state legal_zip 10043 10043 Logan Generating Company US Operating Services Company

operator 9405 Arrowpoint Blvd Charlotte NC 28273

Page 1Facility _Information

plant_name

physical_address

phyical_city

physical_state

physical_zip

mailing_address

mailing_city

mailing_state

mailing_zip Logan Generating Plant

76 Route 130

Swedesboro

NJ 08085 76 Route 130 Swedesboro

NJ 08085

Page 2Facility _Information

RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas No TRUE TRUE FALSE FALSE FALSE TRUE TRUE FALSE

Page 3Facility _Information

ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE FALSE Title V semi-annual and annual deviation reports No EPA Region 2

Page 4facility _contacts

facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 10043 2 General Manager James Sousa

8562414571 FALSE 10043 3 Environmental Manager Philip Fontenelle

8562414575 TRUE

Page 5facility _coal_utilized

facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note 10043 bitum inous 100 100

Page 6facility _oil_utilized

facility _id oil_type percentage_volume percentage_btu

other_type 10043 No.2 Fuel Oil (distillate) 100 100

Page 7facility _other_materials

facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain

Page 8facility _other_materials

rcra_explain

Page 9boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuelheat_input max_heat_input MWe_capacity 10043 B01 Wall firing - opposed firing Dry Bottom coal 2116 2116 241.7

Page 10boiler_information

MWe_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 220.7 88.1 87.5 2500 2400 1005 1000 FALSE 1005

Page 11boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 1000 7921 72.86 Subpart Da(1) FALSE

Page 12boiler_information

NOx_control

SO2_control

combustion_additives Yes No No

Page 13boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 10043 B01 coal - bituminous2007 99.9 99.7 10043 B01 coal - bituminous2008 99.9 99.8 10043 B01 coal - bituminous2009 99.6 99.5 10043 B01 oil - distillate 2007 0.1 0.3 10043 B01 oil - distillate 2008 0.1 0.2 10043 B01 oil - distillate 2009 0.4 0.5

Page 14boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online 10043 B01 Low NOx Burner 9/1/1994 10043 B01 Overfire Air 9/1/1994

Page 15boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online

Page 16boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 17facility _units

facility _id unit_id 10043 Uni1

Page 18unit_boilers

facility _id unit_id boiler_id 10043 Uni1 B01

Page 19facility _controls

facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 10043 BH1 PM control Fabric Filter, reverse air FALSE 9/1/1994 10043 SCR1 NOx control Selective Cataly

tic Reduction FALSE 9/1/1994 Ammonia 10043 SDA1 SO2 control Spray dryer type FALSE 9/1/1994

Page 20facility _controls

reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive

27.5 Lime No

Page 21facility _sampling_ports

facility _id sampling_port_id 10043 Flue 1

Page 22facility _stacks

facility _id stack_id stack_height stack_diameter

sack_gas_velocity 10043 Stack 1 430 8.5 100

Page 23configurations

facility _id configuration_id 10043 Unit1

Page 24configuration_components

facility _id configuration_id

component_id

order component_type port_near 10043 Unit1 BH1 4 PM control 10043 Unit1 Flue 1 5 Sam pling Port next 10043 Unit1 SCR1 2 NOx control 10043 Unit1 SDA1 3 SO2 control 10043 Unit1 Stack 1 6 Stack 10043 Unit1 Uni1 1 Unit

Page 25configuration_pollutants1

facility _id configuration_id

pollutant_name

permit_type_1

emlim it_1 emlim it_units_1 avg_period_1

emlim it_2 emlim it_units_2 10043 Unit1 Total Suspended Particulates (TSP) Federal - Title V Operating Permit

0.018 pound per million British Thermal Unit (lb/MMBtu)

1 hour 38.1 pound per hour (lb/hr) 10043 Unit1 PM2.5 (Filterable) Federal - Title V Operating Permit

0.018 pound per million British Thermal Unit (lb/MMBtu)

1 hour 38.1 pound per hour (lb/hr) 10043 Unit1 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.15 pound per million British Thermal Unit (lb/MMBtu)

1 hour 317.4 pound per hour (lb/hr) 10043 Unit1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

0.16 pound per million British Thermal Unit (lb/MMBtu)

1 hour 342.1 pound per hour (lb/hr) 10043 Unit1 VOCs Federal - Title V Operating Permit 0.0036 pound per million British Thermal Unit (lb/MMBtu)

1 hour 7.6 pound per hour (lb/hr) 10043 Unit1 Carbon Monoxide (CO) Federal - Title V Operating Permit

0.11 pound per million British Thermal Unit (lb/MMBtu)

1 hour 232.8 pound per hour (lb/hr) 10043 Unit1 Lead (Pb) Federal - Title V Operating Permit 0.01 pound per hour (lb/hr)

1 hour 10043 Unit1 Hydrogen Fluoride (HF) Federal - Title V Operating Permit

2.28 pound per hour (lb/hr)

1 hour 10043 Unit1 Hydrogen Chloride (HCl) Federal - Title V Operating Permit

18.4 pound per hour (lb/hr)

1 hour 10043 Unit1 Arsenic (As) Federal - Title V Operating Permit

0.0327 pound per hour (lb/hr)

1 hour 10043 Unit1 Beryllium(Be) Federal - Title V Operating Permit

0.0033 pound per hour (lb/hr)

1 hour 10043 Unit1 Cadmium (Cd) Federal - Title V Operating Permit

0.0046 pound per hour (lb/hr)

1 hour 10043 Unit1 Chromium (Cr) Federal - Title V Operating Permit

0.09 pound per hour (lb/hr)

1 hour 10043 Unit1 Cobalt (Co)Federal - Title V Operating Permit 0.09 pound per hour (lb/hr)

1 hour 10043 Unit1 Manganese (Mn) Federal - Title V Operating Permit

2.28 pound per hour (lb/hr)

1 hour 10043 Unit1 Total Mercury (Hgt) Federal - Title V Operating Permit

0.0106 pound per hour (lb/hr)

1 hour 10043 Unit1 Nickel (Ni) Federal - Title V Operating Permit 1.82 pound per hour (lb/hr)

1 hour 10043 Unit1 Phosphorus (P) Federal - Title V Operating Permit

4.01 pound per hour (lb/hr)

1 hour 10043 Unit1 Selenium(Se) Federal - Title V Operating Permit

1.1 pound per hour (lb/hr)

1 hour 10043 Unit1 Formaldehyde Federal - Title V Operating Permit

0.47 pound per hour (lb/hr)

1 hour 10043 Unit1 Polycyclic Organic Matter (POM) Federal - Title V Operating Permit

0.04 pound per hour (lb/hr)

1 hour

Page 26configuration_pollutants1

avg_period_2

emlim it_3 emlim it_units_3 avg_period_3

emlim it_4 emlim it_units_4 avg_period_4

emlim it_details

test_method 1 hour 1 hour 1 hour 90 parts per million by volume (dry) (ppmvd) 1 hour 1 hour 75 parts per million by volume (dry) (ppmvd) 1 hour 1 hour 1 hour 100 parts per million by volume (dry) (ppmvd) 1 hour

Page 27configuration_pollutants1

emrate emrate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping

req_reporting 38 pound per hour (lb/hr)

Yes 99.9 % efficiency Stak Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2

0.15 pound per million British Thermal Unit (lb/MMBtu)

Yes 70% CEM & Stack Test DAS & Stack Test Results

Subm it Stack Test Results to NJDEP & EPA Region 2 0.16 pound per million British Thermal Unit (lb/MMBtu)

Yes 93% CEM & Stack Test DAS & Stack Test Results

Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 CEM & Stack Test

DAS & Stack Test Results

Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & EPA Region 2 Stack Test Stack Test Results Subm it Stack Test Results to NJDEP & Epa Region 2

Page 28configuration_pollutants1

Subm it Stack Test Results to NJDEP & EPA Region 2

Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & EPA Region 2 Subm it Stack Test Results to NJDEP & Epa Region 2

Page 29control_technologies

facility _id configuration_id

component_id

control_id project_titleproject_type vendor_name

vndor_contact

vendor_phone

Page 30control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 31control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 32control_technologies

feed_rate_units

Page 33control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 34control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_name

Page 35control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investment

total_operating_costs

base_year

Page 36control_costs

CBI

Page 37misc_controls

facility _id misc_control_id

control_description

Page 38misc_control_configurations

facility _id misc_control_id

configuration_id

Page 39fuel_shipments

facility _id shipment_id

shipment_date

amount_received

amount_units

fuel_type state_country other_country

county 10043 M01 1/1/2009 63573 short tons (2000 lbs) coal WV WV- Webster 10043 M02 2/1/2009 47965 short tons (2000 lbs) coal WV WV- Webster 10043 M03 3/1/2009 47938 short tons (2000 lbs) coal WV WV- Webster 10043 M04 4/1/2009 15973 short tons (2000 lbs) coal WV WV- Webster 10043 M05 5/1/2009 32013 short tons (2000 lbs) coal WV WV- Webster 10043 M06 6/1/2009 31807 short tons (2000 lbs) coal WV WV- Webster 10043 M07 7/1/2009 32000 short tons (2000 lbs) coal WV WV- Webster 10043 M08 8/1/2009 23993 short tons (2000 lbs) coal WV WV- Webster 10043 M09 9/1/2009 23985 short tons (2000 lbs) coal WV WV- Webster 10043 M10 10/1/2009 31982 short tons (2000 lbs) coal WV WV- Webster 10043 M11 11/1/2009 32009 short tons (2000 lbs) coal WV WV- Webster 10043 M12 12/1/2009 23988 short tons (2000 lbs) coal WV WV- Webster 10043 MFO-1 1/1/2009 179 barrels oil 10043 MFO-10 10/1/2009 719 barrels oil 10043 MFO-11 11/1/2009 900 barrels oil 10043 MFO-12 12/1/2009 1450 barrels oil 10043 MFO-2 2/1/2009 357 barrels oil 10043 MFO-3 3/1/2009 893 barrels oil 10043 MFO-4 4/1/2009 536 barrels oil 10043 MFO-5 5/1/2009 1503 barrels oil 10043 MFO-6 6/1/2009 1098 barrels oil 10043 MFO-7 7/1/2009 726 barrels oil 10043 MFO-8 8/1/2009 905 barrels oil 10043 MFO-9 9/1/2009 940 barrels oil

Page 40fuel_shipments

coal_seam shipment_method Birch River Mine

Barge Birch River Mine

Barge Birch River Mine

Barge Birch River Mine Birch River Mine

Barge Birch River Mine

Barge Birch River Mine

Barge Birch River Mine

Barge Birch River Mine

Barge Birch River Mine

Barge Birch River Mine

Barge Birch River Mine

Barge

Page 41fuel_shipment_configurations

facility _id shipment_id

configuration_id 10043 M01 Unit1 10043 M02 Unit1 10043 M03 Unit1 10043 M04 Unit1 10043 M05 Unit1 10043 M06 Unit1 10043 M07 Unit1 10043 M08 Unit1 10043 M09 Unit1 10043 M10 Unit1 10043 M11 Unit1 10043 M12 Unit1 10043 MFO-1 Unit1 10043 MFO-10 Unit1 10043 MFO-11 Unit1 10043 MFO-12 Unit1 10043 MFO-2 Unit1 10043 MFO-3 Unit1 10043 MFO-4 Unit1 10043 MFO-5 Unit1 10043 MFO-6 Unit1 10043 MFO-7 Unit1 10043 MFO-8 Unit1

Page 42fuel_shipment_samples

facility _id shipment_id

sample_id amount_fuel amount_fuel_units

total_sulfur ash_content heating_value

hating_units 10043 M01 M01 63573 tons 1.33 9.9 12695 Btu/lb 10043 M02 M02 47965 tons 1.2 9.9 12690 Btu/lb 10043 M03 M03 47938 tons 1.1 10.4 12645 Btu/lb 10043 M04 M04 15973 tons 1.07 10.1 12385 Btu/lb 10043 M05 M05 32013 tons 1.15 10 12545 Btu/lb 10043 M06 M06 31807 tons 1.25 9.9 12680 Btu/lb 10043 M07 M07 32000 tons 1.19 10.2 12660 Btu/lb 10043 M08 M08 23993 tons 1.11 9.7 12690 Btu/lb 10043 M09 M09 23985 tons 1.07 9.7 12740 Btu/lb 10043 M10 M10 31892 tons 1.22 9.8 12765 Btu/lb 10043 M11 M11 32009 tons 1.21 9.3 12855 Btu/lb 10043 M12 M12 23988 tons 1.19 9 12755 Btu/lb 10043 MFO-1 MFO-1 7500 gallons 0.16 18882 Btu/lb 10043 MFO-10 MFO-10 30208 gallons 0.17 18661 Btu/lb 10043 MFO-11 MFO-11 37809 gallons 0.14 18759 Btu/lb 10043 MFO-12 MFO-12 60910 gallons 0.14 18693 10043 MFO-2 MFO-2 15000 gallons 0.17 18693 Btu/lb 10043 MFO-3 MFO-3 37513 gallons 0.18 18267 Btu/lb 10043 MFO-4 MFO-4 22510 gallons 0.18 19284 Btu/lb 10043 MFO-5 MFO-5 63113 gallons 0.07 18562 Btu/lb 10043 MFO-6 MFO-6 46104 gallons 0.15 18693 Btu/lb 10043 MFO-7 MFO-7 30510 gallons 0.18 18726 Btu/lb 10043 MFO-8 MFO-8 38008 gallons 0.2 18693 Btu/lb 10043 MFO-9 MFO-9 39500 gallons

Page 43fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier permit requirements Fuel supplier

Page 44fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_name lab_address lab_city lab_state lab_zip analysis_copies Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes

Page 45fuel_shipment_samples

analysis_copies

Page 46fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL 10043 M01 M01 Mercury (Hg) 0.177 percent (dry) (%) FALSE 10043 M02 M02 Mercury (Hg) 0.156 percent (dry) (%) FALSE 10043 M03 M03 Mercury (Hg) 0.104 percent (dry) (%) FALSE 10043 M04 M04 Mercury (Hg) 0.175 percent (dry) (%) FALSE 10043 M05 M05 Mercury (Hg) 0.134 percent (dry) (%) FALSE 10043 M06 M06 Mercury (Hg) 0.165 percent (dry) (%) FALSE 10043 M07 M07 Mercury (Hg) 0.135 percent (dry) (%) FALSE 10043 M08 M08 Mercury (Hg) 0.132 percent (dry) (%) FALSE 10043 M09 M09 Mercury (Hg) 0.152 percent (dry) (%) FALSE 10043 M10 M10 Mercury (Hg) 0.122 percent (dry) (%) FALSE 10043 M11 M11 Mercury (Hg) percent (dry) (%) TRUE 10043 M12 M12 Mercury (Hg) 0.115 percent (dry) (%) FALSE

Page 47test_reports

facility _id report_id report_typeother_type report_description report_begin_date

report_end_date

before_control

during_deviation 10043 2005 Annual Stack Test 6

compliance Annual Stack Test 5/19/2005 5/19/2005 No No 10043 2005 Annual Stack Test 7

compliance Annual Stack Test 6/23/2005 6/25/2005 No No 10043 2005 Annual Stack Test-1

compliance Annual Stack Test 5/19/2008 5/20/2008 No No 10043 2005 Annual Stack Test-2

compliance Annual Stack Test 6/15/2006 6/16/2006 No No 10043 2005 Annual Stack Test-3

compliance Annual Stack Test 7/10/2007 7/12/2007 No No 10043 2005 Annual Stack Test-4

compliance Annual Stack Test 6/25/2008 6/27/2008 No No 10043 2006 Annual Stack Test 4

compliance Annual Stack Test 6/15/2006 6/15/2006 No No 10043 2006 Annual Stack Test 1

compliance Annual Stack Test 6/15/2006 6/16/2006 No No 10043 2006 Annual Stack Test 2

compliance 6/15/2006 6/16/2006 No No 10043 2006 Annual Stack Test 3

compliance Annual Stack Test 6/15/2006 6/16/2006 No No 10043 2006 Annual Stack Test 5

compliance Annual Stack Test 6/16/2006 6/16/2006 No No 10043 2007 Annual Stack Test 1

compliance Annual Stack Test 7/10/2007 7/12/2007 No No 10043 2007 Annual Stack Test 2

compliance Annual Stack Test 7/10/2007 7/12/2007 No No 10043 2007 Annual Stack Test 3

compliance Annual Stack Test 7/12/2007 7/12/2007 No No 10043 2007 Annual Stack Test 4

compliance Annual Stack Test 7/10/2007 7/12/2007 No No 10043 2007 Annual Stack Test 5

compliance Annual Stack Test 7/10/2007 7/12/2007 No No 10043 2007 Annual Stack Test 6

compliance Annual Stack Test 7/11/2007 7/12/2007 No No 10043 2008 Annual Stack Test 2

compliance Annual Stack Test 6/25/2008 6/27/2008 No No 10043 2008 Annual Stack Test 3

compliance Annual Stack Test 6/25/2008 6/27/2008 No No 10043 2008 Annual Stack Test 4

compliance Annual Stack Test 6/25/2008 6/25/2008 No No 10043 2008 Annual Stack testing 1

compliance Annual Stack Testing 6/25/2008 6/27/2008 No No 10043 2008 Stack Test 5

compliance Annual Stack Test 6/25/2008 6/27/2008 No No 10043 2009 Annual Stack Test 1

compliance Annual Stack Test 6/23/2009 6/25/2009 No No 10043 2009 Annual Stack Test 2

compliance Annual Stack Test 6/23/2009 6/25/2009 No No 10043 2009 Annual Stack Test 3

compliance Annual Stack Test 6/23/2009 6/25/2009 No No 10043 2009 Annual Stack Test 4

compliance Annual Stack Test No No 10043 2009 Annual Stack Test 5

compliance Annual Stack Test 6/23/2009 6/25/2009 No No

Page 48test_reports

deviation_reports No No No No No No No No No No No No No No No No No No No No No No No No No No No

Page 49test_report_configurations

facility _id report_id configuration_id 10043 2005 Annual Stack Test 6

Unit1 10043 2005 Annual Stack Test 7

Unit1 10043 2005 Annual Stack Test-1

Unit1 10043 2005 Annual Stack Test-2

Unit1 10043 2005 Annual Stack Test-3

Unit1 10043 2005 Annual Stack Test-4

Unit1 10043 2006 Annual Stack Test 4

Unit1 10043 2006 Annual Stack Test 1

Unit1 10043 2006 Annual Stack Test 2

Unit1 10043 2006 Annual Stack Test 3

Unit1 10043 2006 Annual Stack Test 5

Unit1 10043 2007 Annual Stack Test 1

Unit1 10043 2007 Annual Stack Test 2

Unit1 10043 2007 Annual Stack Test 3

Unit1 10043 2007 Annual Stack Test 4

Unit1 10043 2007 Annual Stack Test 5

Unit1 10043 2007 Annual Stack Test 6

Unit1 10043 2008 Annual Stack Test 2

Unit1 10043 2008 Annual Stack Test 3

Unit1 10043 2008 Annual Stack Test 4

Unit1 10043 2008 Annual Stack testing 1

Unit1 10043 2008 Stack Test 5

Unit1 10043 2009 Annual Stack Test 1

Unit1 10043 2009 Annual Stack Test 2

Unit1 10043 2009 Annual Stack Test 3

Unit1 10043 2009 Annual Stack Test 4

Unit1 10043 2009 Annual Stack Test 5

Unit1

Page 50test_report_fuels

facility _id report_id fuel_id 10043 2005 Annual Stack Test 6

Coal 10043 2005 Annual Stack Test 7

Coal 10043 2005 Annual Stack Test-1

Coal 10043 2005 Annual Stack Test-2

Coal 10043 2005 Annual Stack Test-3

Coal 10043 2005 Annual Stack Test-4

Coal 10043 2006 Annual Stack Test 4

Coal 10043 2006 Annual Stack Test 1

Coal 10043 2006 Annual Stack Test 2

Coal 10043 2006 Annual Stack Test 3

Coal 10043 2006 Annual Stack Test 5

Coal 10043 2007 Annual Stack Test 1

Coal 10043 2007 Annual Stack Test 2

Coal 10043 2007 Annual Stack Test 3

Coal 10043 2007 Annual Stack Test 4

Coal 10043 2007 Annual Stack Test 5

Coal 10043 2007 Annual Stack Test 6

Coal 10043 2008 Annual Stack Test 2

Coal 10043 2008 Annual Stack Test 3

Coal 10043 2008 Annual Stack Test 4

Coal 10043 2008 Annual Stack testing 1

Coal 10043 2008 Stack Test 5

Coal 10043 2009 Annual Stack Test 1

Coal 10043 2009 Annual Stack Test 2

Coal 10043 2009 Annual Stack Test 3

Coal 10043 2009 Annual Stack Test 4

Coal 10043 2009 Annual Stack Test 5

Coal

Page 51test_report_fuel_types

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 10043 2005 Annual Stack Test 6

Coal coal - bituminous 100 100 10043 2005 Annual Stack Test 7

Coal coal - bituminous 100 100 10043 2005 Annual Stack Test-1

Coal coal - bituminous 100 100 10043 2005 Annual Stack Test-2

Coal coal - bituminous 100 100 10043 2005 Annual Stack Test-3

Coal coal - bituminous 100 100 10043 2005 Annual Stack Test-4

Coal coal - bituminous 100 100 10043 2006 Annual Stack Test 4

Coal coal - bituminous 100 100 10043 2006 Annual Stack Test 1

Coal coal - bituminous 100 100 10043 2006 Annual Stack Test 2

Coal coal - bituminous 100 100 10043 2006 Annual Stack Test 3

Coal coal - bituminous 100 100 10043 2006 Annual Stack Test 5

Coal coal - bituminous 100 100 10043 2007 Annual Stack Test 1

Coal coal - bituminous 100 100 10043 2007 Annual Stack Test 2

Coal coal - bituminous 100 100 10043 2007 Annual Stack Test 3

Coal coal - bituminous 100 100 10043 2007 Annual Stack Test 4

Coal coal - bituminous 100 100 10043 2007 Annual Stack Test 5

Coal coal - bituminous 100 100 10043 2007 Annual Stack Test 6

Coal coal - bituminous 100 100 10043 2008 Annual Stack Test 2

Coal coal - bituminous 100 100 10043 2008 Annual Stack Test 3

Coal coal - bituminous 100 100 10043 2008 Annual Stack Test 4

Coal coal - bituminous 100 100 10043 2008 Annual Stack testing 1

Coal coal - bituminous 100 100 10043 2008 Stack Test 5

Coal coal - bituminous 100 100 10043 2009 Annual Stack Test 1

Coal coal - bituminous 100 100 10043 2009 Annual Stack Test 2

Coal coal - bituminous 100 100 10043 2009 Annual Stack Test 3

Coal coal - bituminous 100 100 10043 2009 Annual Stack Test 4

Coal coal - bituminous 100 100 10043 2009 Annual Stack Test 5

Coal coal - bituminous 100 100

Page 52cem_data

facility _id time_period

cem_period_description 10043 2005-2009

Page 53cem_data_pollutants1

facility _id time_period

pollutant_name 10043 2005-2009 Nitrogen Oxide (NOx) 10043 2005-2009 Sulfur Dioxide (SO2) 10043 2005-2009 Carbon Monoxide (CO)

Page 54test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_bypass_percent

testing_bypass_percent 10043 2005 Annual Stack Test 6

Flue 1 No Hydrogen Chloride No 10043 2005 Annual Stack Test 7

Flue 1 No Hydrogen Flouride No 10043 2005 Annual Stack Test-1

Flue 1 No TSP No 10043 2005 Annual Stack Test-2

Flue 1 No PM-10 No 10043 2005 Annual Stack Test-3

Flue 1 No NOx , CO, SO2 & VOC No 10043 2005 Annual Stack Test-4

Flue 1 No Toxic Metals No 10043 2006 Annual Stack Test 4

Flue 1 No PM-10 No 10043 2006 Annual Stack Test 1

Flue 1 No TSP No 10043 2006 Annual Stack Test 2

Flue 1 No Hydrogen Flooride No 10043 2006 Annual Stack Test 3

Flue 1 No Toxic Metals No 10043 2006 Annual Stack Test 5

Flue 1 No HF No 10043 2007 Annual Stack Test 1

Flue 1 No TSP No 10043 2007 Annual Stack Test 2

Flue 1 No HF No 10043 2007 Annual Stack Test 3

Flue 1 No HCl No 10043 2007 Annual Stack Test 4

Flue 1 No Toxic Metals No 10043 2007 Annual Stack Test 5

Flue 1 No PM-10 No 10043 2007 Annual Stack Test 6

Flue 1 No Polycyclic Organic Matter (POC) No 10043 2008 Annual Stack Test 2

Flue 1 No Hydrogen Fluoride No 10043 2008 Annual Stack Test 3

Flue 1 No Hydrogen Chloride No 10043 2008 Annual Stack Test 4

Flue 1 No Toxic Metals No 10043 2008 Annual Stack testing 1

Flue 1 No Total Suspended Particulate Matter No 10043 2008 Stack Test 5

Flue 1 No PM-10 No 10043 2009 Annual Stack Test 1

Flue 1 No TSP No 10043 2009 Annual Stack Test 2

Flue 1 No Hydrogen Fluoride No 10043 2009 Annual Stack Test 3

Flue 1 No Hydrogen Chloride No 10043 2009 Annual Stack Test 4

Flue 1 No Toxic Metals No 10043 2009 Annual Stack Test 5

Flue 1 No PM-10 No

Page 55test_report_sampling

fg_fraction

Page 56sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetime

unit_load net_generation fg_moisture_content 10043 2005 Annual Stack Test 6

Flue 1 1 5/19/2005 5/19/2005 10.6 10043 2005 Annual Stack Test 6

Flue 1 2 5/19/2005 5/19/2005 11.3 10043 2005 Annual Stack Test 6

Flue 1 3 5/19/2005 5/19/2005 11.4 10043 2005 Annual Stack Test 7

Flue 1 1 5/19/2005 5/19/2005 10.36 10043 2005 Annual Stack Test 7

Flue 1 2 5/19/2005 5/19/2005 10.6 10043 2005 Annual Stack Test 7

Flue 1 3 5/19/2005 5/19/2005 17.8 10043 2005 Annual Stack Test-1

Flue 1 1 5/19/2005 5/20/2005 9.83 10043 2005 Annual Stack Test-1

Flue 1 2 5/19/2005 5/20/2005 10.5 10043 2005 Annual Stack Test-1

Flue 1 3 5/19/2005 5/20/2005 10.7 10043 2005 Annual Stack Test-2

Flue 1 1 5/19/2005 5/19/2005 10.4 10043 2005 Annual Stack Test-2

Flue 1 2 5/19/2005 5/19/2005 9.1 10043 2005 Annual Stack Test-2

Flue 1 3 5/19/2005 5/19/2005 9.9 10043 2005 Annual Stack Test-2

Flue 1 4 5/19/2005 5/19/2005 9.5 10043 2005 Annual Stack Test-3

Flue 1 1 5/19/2005 5/19/2005 243.3 10.4 10043 2005 Annual Stack Test-3

Flue 1 2 5/19/2005 5/19/2005 243.3 9.1 10043 2005 Annual Stack Test-3

Flue 1 3 5/19/2005 5/19/2005 243.8 9.9 10043 2005 Annual Stack Test-3

Flue 1 4 5/19/2005 5/19/2005 242.3 9.5 10043 2005 Annual Stack Test-4

Flue 1 1 5/19/2005 5/19/2005 11 10043 2005 Annual Stack Test-4

Flue 1 2 5/19/2005 5/19/2005 10.7 10043 2005 Annual Stack Test-4

Flue 1 3 5/19/2005 5/19/2005 10.6 10043 2006 Annual Stack Test 4

Flue 1 1 6/15/2006 6/15/2006 10.9 10043 2006 Annual Stack Test 4

Flue 1 2 6/15/2006 6/15/2006 10.7 10043 2006 Annual Stack Test 4

Flue 1 3 6/15/2006 6/15/2006 10.8 10043 2006 Annual Stack Test 1

Flue 1 1 6/15/2006 6/15/2006 11.2 10043 2006 Annual Stack Test 1

Flue 1 2 6/15/2006 6/15/2006 10.9 10043 2006 Annual Stack Test 1

Flue 1 3 6/16/2006 6/16/2006 11.1 10043 2006 Annual Stack Test 2

Flue 1 1 6/15/2006 6/15/2006 10.5 10043 2006 Annual Stack Test 2

Flue 1 2 6/15/2006 6/15/2006 10.7 10043 2006 Annual Stack Test 2

Flue 1 3 6/16/2006 6/16/2006 10.7 10043 2006 Annual Stack Test 3

Flue 1 1 6/15/2006 6/15/2006 10.9 10043 2006 Annual Stack Test 3

Flue 1 2 6/15/2006 6/15/2006 10.9 10043 2006 Annual Stack Test 3

Flue 1 3 6/16/2006 6/16/2006 10.3 10043 2006 Annual Stack Test 5

Flue 1 1 6/16/2006 6/16/2006 11.4 10043 2006 Annual Stack Test 5

Flue 1 2 6/16/2006 6/16/2006 11.7 10043 2006 Annual Stack Test 5

Flue 1 3 6/16/2006 6/16/2006 11.4 10043 2007 Annual Stack Test 1

Flue 1 1 7/11/2007 7/11/2007 12.6 10043 2007 Annual Stack Test 1

Flue 1 2 7/11/2007 7/11/2007 12.6 10043 2007 Annual Stack Test 1

Flue 1 3 7/11/2007 7/11/2007 12.3 10043 2007 Annual Stack Test 2

Flue 1 1 7/11/2007 7/11/2007 13.1 10043 2007 Annual Stack Test 2

Flue 1 2 7/11/2007 7/11/2007 12.9 10043 2007 Annual Stack Test 2

Flue 1 3 7/11/2007 7/11/2007 13 10043 2007 Annual Stack Test 3

Flue 1 1 7/12/2007 7/12/2007 11.9 10043 2007 Annual Stack Test 3

Flue 1 2 7/12/2007 7/12/2007 11.9 10043 2007 Annual Stack Test 3

Flue 1 3 7/12/2007 7/12/2007 11.1 10043 2007 Annual Stack Test 4

Flue 1 1 7/10/2007 7/10/2007 11.1 10043 2007 Annual Stack Test 4

Flue 1 2 7/10/2007 7/10/2007 12.9 10043 2007 Annual Stack Test 4

Flue 1 3 7/10/2007 7/10/2007 12.8 10043 2007 Annual Stack Test 5

Flue 1 1 7/10/2007 7/10/2007 11.6 10043 2007 Annual Stack Test 5

Flue 1 2 7/10/2007 7/10/2007 11.1 10043 2007 Annual Stack Test 5

Flue 1 3 7/10/2007 7/10/2007 12.4 10043 2007 Annual Stack Test 6

Flue 1 1 7/11/2007 7/11/2007 12.1

Page 57sampling_runs

10043 2007 Annual Stack Test 6

Flue 1 2 7/11/2007 7/11/2007 13.1 10043 2007 Annual Stack Test 6

Flue 1 3 7/12/2007 7/12/2007 11.8 10043 2008 Annual Stack Test 2

Flue 1 1 6/27/2008 6/27/2008 11.6 10043 2008 Annual Stack Test 2

Flue 1 2 6/27/2008 6/27/2008 12.3 10043 2008 Annual Stack Test 2

Flue 1 3 6/27/2008 6/27/2008 13 10043 2008 Annual Stack Test 3

Flue 1 1 6/27/2008 6/27/2008 10.9 10043 2008 Annual Stack Test 3

Flue 1 2 6/27/2008 6/27/2008 11.5 10043 2008 Annual Stack Test 3

Flue 1 3 6/27/2008 6/27/2008 11.6 10043 2008 Annual Stack Test 4

Flue 1 1 6/25/2008 6/25/2008 11.7 10043 2008 Annual Stack Test 4

Flue 1 2 6/25/2008 6/25/2008 11.9 10043 2008 Annual Stack Test 4

Flue 1 3 6/25/2008 6/25/2008 11.8 10043 2008 Annual Stack testing 1

Flue 1 1 6/26/2008 6/26/2008 13.3 10043 2008 Annual Stack testing 1

Flue 1 2 6/26/2008 6/26/2008 13.2 10043 2008 Annual Stack testing 1

Flue 1 3 6/26/2008 6/26/2008 13.3 10043 2008 Stack Test 5

Flue 1 1 6/26/2008 6/26/2008 11.6 10043 2008 Stack Test 5

Flue 1 2 6/26/2008 6/26/2008 9.9 10043 2008 Stack Test 5

Flue 1 3 6/26/2008 6/26/2008 10.3 10043 2009 Annual Stack Test 1

Flue 1 1 6/24/2009 6/24/2009 11.5 10043 2009 Annual Stack Test 1

Flue 1 2 6/24/2009 6/24/2009 12.3 10043 2009 Annual Stack Test 1

Flue 1 3 6/24/2009 6/24/2009 13.1 10043 2009 Annual Stack Test 2

Flue 1 1 6/25/2009 6/25/2009 12.6 10043 2009 Annual Stack Test 2

Flue 1 2 6/25/2009 6/25/2009 13.4 10043 2009 Annual Stack Test 2

Flue 1 3 6/25/2009 6/25/2009 12.6 10043 2009 Annual Stack Test 3

Flue 1 1 6/24/2009 6/24/2009 12.1 10043 2009 Annual Stack Test 3

Flue 1 2 6/24/2009 6/24/2009 12.1 10043 2009 Annual Stack Test 3

Flue 1 3 6/24/2009 6/24/2009 12.6 10043 2009 Annual Stack Test 4

Flue 1 1 6/23/2009 6/23/2009 12.2 10043 2009 Annual Stack Test 4

Flue 1 2 6/23/2009 6/23/2009 12.1 10043 2009 Annual Stack Test 4

Flue 1 3 6/23/2009 6/23/2009 11.9 10043 2009 Annual Stack Test 5

Flue 1 1 6/23/2009 6/23/2009 10.5 10043 2009 Annual Stack Test 5

Flue 1 2 6/23/2009 6/23/2009 10.3 10043 2009 Annual Stack Test 5

Flue 1 3 6/23/2009 6/23/2009 11

Page 58sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 543281 dscfm 70 1 6.5 12.9 186 535020 dscfm 70 1 5.7 13.7 185 524479 dscfm 70 1 5.5 13.7 168.8 535434 dscfm 70 1 6.5 12.9 185.9 537120 dscfm 70 1 5.7 13.7 184.3 492246 dscfm 70 1 5.5 13.7 185.2 534422 dscfm 70 1 6 13.4 187 530092.5 dscfm 70 1 6 13.3 186 527419 dscfm 70 1 6.2 13.1 187 557183 dscfm 76 1 5.97 13.37 188 570500 dscfm 6 13.3 187 559153 dscfm 84 1 6.21 13.1 188 574796 dscfm 84 1 6.5 12.9 187 557183 dscfm 70 1 6 10.4 570500 dscfm 70 1 6 13.3 559153 dscfm 70 1 6.2 13.1 574796 dscfm 70 1 6.5 12.9 513224.5 dscfm 70 1 6 13.4 186 501231.5 dscfm 70 1 6 13.3 185.7 525562.5 dscfm 70 1 6.2 13.1 184.6 549258 dscfm 70 1 6.3 14 188 536012 dscfm 70 1 5.9 14.1 186 549232 dscfm 70 1 5.8 14.2 188 507477 dscfm 70 1 10 10 186 514014 dscfm 70 1 5 13.9 187 497531 dscfm 70 1 6.9 12.2 185 523607 dscfm 70 1 10 10 189 518558 dscfm 70 1 5 13.9 189 512890 dscfm 70 1 6.9 12.2 186 529756 dscfm 70 1 6.3 14 186 507826 dscfm 70 1 5.9 14.1 185 529218 dscfm 70 1 5 14.2 185 511345 dscfm 70 1 7.3 11 188 496031 dscfm 70 1 7.2 10.9 189 504591 dscfm 70 1 7.2 10.9 189 527992 dscfm 70 1 5.5 13 182 524615 dscfm 70 1 5.5 13 183 532942 dscfm 5.5 13 183 527477 dscfm 70 1 5.7 12.2 182 531081 dscfm 70 1 5.7 12.2 183 519569 dscfm 70 1 5.7 12.2 183 507728 dscfm 70 1 5.8 12.1 185 507728 dscfm 70 1 5.8 12.1 185 530382 dscfm 70 1 5.8 12.1 184 523533 dscfm 70 1 5.7 12 530543 dscfm 70 1 5.9 13.5 186 524872 dscfm 70 1 5.5 13.5 185 553187 dscfm 70 1 5.7 12 184 557731 dscfm 70 1 5.9 13.5 184 549118 dscfm 70 1 5.5 13.5 183 520494 dscfm 70 1 5.5 13 186

Page 59sampling_runs

524969 dscfm 70 1 5.7 12.2 186 532501 dscfm 70 1 5.8 12.1 187 547076 dscfm 70 1 6 13.2 190 548694 dscfm 70 1 5.7 13.5 190 540930 dscfm 70 1 5.6 13.7 190 550079 dscfm 70 1 6 13.2 188 546697 dscfm 70 1 5.7 13.5 188 547384 dscfm 70 1 5.6 13.7 188 528382 dscfm 70 1 5.7 13.7 187 527181 dscfm 70 1 5.6 13.9 187 524290 dscfm 70 1 5.7 13.7 185 518735 dscfm 70 1 5.6 13.9 188 532251 dscfm 70 1 5.4 13.3 188 532593 dscfm 70 1 5.5 14.2 188 554517 dscfm 70 1 5.6 13.9 187 650488 dscfm 70 1 5.4 14.3 187 564510 dscfm 70 1 5.5 14.2 187 518715 dscfm 70 1 6.1 13.6 188 509296 dscfm 70 1 6.1 13.5 189 501891 dscfm 70 1 6 13.6 188 523998 dscfm 70 1 5.3 14.3 189 527535 dscfm 70 1 5.4 14.3 189 532910 dscfm 70 1 6 13.6 189 533811 dscfm 70 1 6.1 13.6 190 535465 dscfm 70 1 6.1 13.5 190 532910 dscfm 70 1 6 13.6 189 532608 dscfm 70 1 5.7 13.9 187 524712 dscfm 70 1 5.8 13.9 187 534183 dscfm 70 1 6 13.6 187 552671 dscfm 70 1 5.7 13.9 190 554339 dscfm 70 1 5.8 13.9 191 553983 dscfm 70 1 6 13.6 191

Page 60sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value EPA 26A EPA 26A EPA 26A EPA 13B EPA 13B EPA 13B EPA 29

NJATM-1 201A/202 201A/202 201A/202 201A/202 EPA 6C, 7E, 10 and 25A 6C, 7E, 10 & 25A EPA 6C, 7E, 10 & 25A EPA 6C, 7E, 10 & 25A EPA 29 EPA 29 EPA 29 EPA 201A/202 EPA 210A/202 EPA 201A/202 NJATM-1 NJATM-1 NJATM-1 EPA 26A EPA 26A EPA 26A EPA 29 EPA 29 EPA 29 EPA 13B EPA 13B EPA 13B NJATM-1 NJATM-1 NJATM-1 EPA 13B EPA 13B EPA 13B EPA 26A EPA 26A EPA 26A EPA 29 EPA 29 EPA 29 EPA 201A/202 EPA 201A/202 EPA 201A/202 EPA 23

Page 61sampling_runs

EPA 23 EPA 23 EPA 13B EPA 13B NJATM-1 EPA 26A EPA 26A EPA 26A EPA 29 EPA 29 EPA 29 NJATM-1 NJATM-1 NJATM-1 EPA 201A/202 EPA 201A/202 EPA 201A/202 NJATM-1 NJATM-1 NJATM-1 EPA 13B EPA 13B NJATM-1 EPA 26A EPA 26A EPA 26A EPA 29 EPA 29 EPA 29 EPA 201A/202 EPA 201A/202 EPA 201A/202

Page 62sampling_runs

fuel_sulfur

Page 63sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_name conc conc_units conc_ND conc_MDL 10043 2005 Annual Stack Test-1

Flue 1 1 Total Suspended Particulates (TSP) FALSE 10043 2005 Annual Stack Test-1

Flue 1 2 Total Suspended Particulates (TSP) FALSE 10043 2005 Annual Stack Test-1

Flue 1 3 Total Suspended Particulates (TSP) FALSE 10043 2005 Annual Stack Test-2

Flue 1 1 PM10 (Filterable) FALSE 10043 2005 Annual Stack Test-2

Flue 1 2 PM10 (Filterable) FALSE 10043 2005 Annual Stack Test-2

Flue 1 3 PM10 (Filterable) FALSE 10043 2005 Annual Stack Test-2

Flue 1 4 PM10 (Filterable) FALSE 10043 2005 Annual Stack Test-3

Flue 1 1 Nitrogen Oxide (NOx) 76.5 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-3

Flue 1 1 Carbon Monoxide (CO) 60.1 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-3

Flue 1 1 Sulfur Dioxide (SO2) 44.4 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-3

Flue 1 1 VOCs 1.79 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-3

Flue 1 2 Nitrogen Oxide (NOx) 74.9 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-3

Flue 1 2 Carbon Monoxide (CO) 41.6 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test 7

Flue 1 1 Hydrogen Fluoride (HF) 0.08 parts per million by volume (dry) (ppmvd) TRUE 10043 2005 Annual Stack Test 7

Flue 1 2 Hydrogen Fluoride (HF) 0.08 parts per million by volume (dry) (ppmvd) TRUE 10043 2005 Annual Stack Test 7

Flue 1 3 Hydrogen Fluoride (HF) 0.23 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test 6

Flue 1 1 Hydrogen Chloride (HCl) 0.04 parts per million by volume (dry) (ppmvd) TRUE 0.04 10043 2005 Annual Stack Test 6

Flue 1 2 Hydrogen Chloride (HCl) 0.08 parts per million by volume (dry) (ppmvd) TRUE 10043 2005 Annual Stack Test 6

Flue 1 3 Hydrogen Chloride (HCl) 16 parts per million by

volume (dry) (ppmvd @ 7% O2) FALSE 10043 2006 Annual Stack Test 1

Flue 1 1 Total Suspended Particulates (TSP) 5.26 milligramper cubic meter (mg/m3)

FALSE 10043 2006 Annual Stack Test 1

Flue 1 2 Total Suspended Particulates (TSP) 6.87 milligramper cubic meter (mg/m3)

FALSE 10043 2006 Annual Stack Test 1

Flue 1 3 Total Suspended Particulates (TSP) 10.76 milligramper cubic meter (mg/m3)

FALSE 10043 2006 Annual Stack Test 2

Flue 1 1 Hydrogen Chloride (HCl) 0.06 parts per million by volume (dry) (ppmvd @ 7% O2) TRUE 10043 2006 Annual Stack Test 2

Flue 1 2 Hydrogen Chloride (HCl) 0.06 parts per million by volume (dry) (ppmvd @ 7% O2) TRUE 10043 2006 Annual Stack Test 2

Flue 1 3 Hydrogen Chloride (HCl) 0.05 parts per million by volume (dry) (ppmvd @ 7% O2) TRUE 10043 2006 Annual Stack Test 3

Flue 1 1 Arsenic (As) TRUE 10043 2006 Annual Stack Test 3

Flue 1 1 Beryllium(Be) TRUE 10043 2006 Annual Stack Test 3

Flue 1 1 Cadmium (Cd) FALSE 10043 2006 Annual Stack Test 3

Flue 1 1 Cobalt (Co) TRUE 10043 2006 Annual Stack Test 3

Flue 1 1 Lead (Pb) TRUE 10043 2006 Annual Stack Test 3

Flue 1 1 Manganese (Mn) FALSE 10043 2006 Annual Stack Test 3

Flue 1 1 Nickel (Ni) TRUE 10043 2006 Annual Stack Test 3

Flue 1 1 Phosphorus (P) TRUE 10043 2006 Annual Stack Test 3

Flue 1 1 Selenium(Se) FALSE 10043 2006 Annual Stack Test 3

Flue 1 1 Total Mercury (Hgt) TRUE 10043 2006 Annual Stack Test 3

Flue 1 2 Arsenic (As) TRUE 10043 2006 Annual Stack Test 3

Flue 1 2 Beryllium(Be) TRUE 10043 2006 Annual Stack Test 3

Flue 1 2 Cadmium (Cd) FALSE 10043 2006 Annual Stack Test 3

Flue 1 2 Chromium (Cr) FALSE 10043 2006 Annual Stack Test 3

Flue 1 2 Cobalt (Co) TRUE 10043 2006 Annual Stack Test 3

Flue 1 2 Lead (Pb) TRUE 10043 2006 Annual Stack Test 3

Flue 1 2 Manganese (Mn) FALSE 10043 2006 Annual Stack Test 3

Flue 1 2 Nickel (Ni) TRUE 10043 2006 Annual Stack Test 3

Flue 1 2 Phosphorus (P) TRUE 10043 2005 Annual Stack Test-3

Flue 1 2 Sulfur Dioxide (SO2) 47.9 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-3

Flue 1 2 VOCs 2.61 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-3

Flue 1 3 Nitrogen Oxide (NOx) 83.1 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-3

Flue 1 3 Carbon Monoxide (CO) 77 parts per million by

volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-3

Flue 1 3 Sulfur Dioxide (SO2) 39.4 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-3

Flue 1 3 VOCs 1.02 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-3

Flue 1 4 Nitrogen Oxide (NOx) 84.4 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE

Page 64sampling_run_pollutants1

10043 2005 Annual Stack Test-3

Flue 1 4 Carbon Monoxide (CO) 38.5 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-3

Flue 1 4 Sulfur Dioxide (SO2) 42 parts per million by

volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-3

Flue 1 4 VOCs 0.87 parts per million by volume (dry) (ppmvd @ 7% O2) FALSE 10043 2005 Annual Stack Test-4

Flue 1 1 Arsenic (As) 478.5 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 1 Beryllium(Be) 0.285 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 1 Cadmium (Cd) 0.926 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 1 Chromium (Cr)55.187 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 1 Cobalt (Co) 2.564 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 1 Lead (Pb) 56.61 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 1 Manganese (Mn) 62.165 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 1 Total Mercury (Hgt) TRUE 10043 2005 Annual Stack Test-4

Flue 1 1 Nickel (Ni) 43.794 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 1 Phosphorus (P) TRUE 10043 2005 Annual Stack Test-4

Flue 1 1 Selenium(Se) 2.848 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 2 Arsenic (As) 420.5 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 2 Beryllium(Be) 0.22 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 2 Cadmium (Cd) 0.726 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 2 Chromium (Cr) 16.706 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 2 Cobalt (Co) 1.816 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 2 Lead (Pb) 49.1 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 2 Manganese (Mn) 45.614 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 2 Total Mercury (Hgt) TRUE 10043 2005 Annual Stack Test-4

Flue 1 2 Nickel (Ni) 15.108 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 2 Phosphorus (P) TRUE 10043 2005 Annual Stack Test-4

Flue 1 2 Selenium(Se) 1.453 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 3 Arsenic (As) 417.5 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 3 Beryllium(Be) 0.213 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 3 Cadmium (Cd) 0.78 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 3 Chromium (Cr) 9.32 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 3 Cobalt (Co) 1.35 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 3 Lead (Pb) 48.22 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 3 Manganese (Mn) 551.91 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 3 Total Mercury (Hgt) TRUE 10043 2005 Annual Stack Test-4

Flue 1 3 Nickel (Ni) 8.39 microgram per dry standard cubic meter ( FALSE 10043 2005 Annual Stack Test-4

Flue 1 3 Phosphorus (P) TRUE 10043 2005 Annual Stack Test-4

Flue 1 3 Selenium(Se) 2.84 microgram per dry standard cubic meter ( FALSE 10043 2006 Annual Stack Test 3

Flue 1 2 Selenium(Se) TRUE 10043 2006 Annual Stack Test 3

Flue 1 2 Total Mercury (Hgt) TRUE 10043 2006 Annual Stack Test 3

Flue 1 3 Arsenic (As) TRUE 10043 2006 Annual Stack Test 3

Flue 1 3 Beryllium(Be) TRUE 10043 2006 Annual Stack Test 3

Flue 1 3 Cadmium (Cd) TRUE 10043 2006 Annual Stack Test 3

Flue 1 3 Chromium (Cr) TRUE 10043 2006 Annual Stack Test 3

Flue 1 3 Cobalt (Co) TRUE 10043 2006 Annual Stack Test 3

Flue 1 3 Lead (Pb) TRUE 10043 2006 Annual Stack Test 3

Flue 1 3 Manganese (Mn) FALSE 10043 2006 Annual Stack Test 3

Flue 1 3 Nickel (Ni) TRUE 10043 2006 Annual Stack Test 3

Flue 1 3 Phosphorus (P) TRUE 10043 2006 Annual Stack Test 3

Flue 1 3 Selenium(Se) FALSE 10043 2006 Annual Stack Test 3

Flue 1 3 Total Mercury (Hgt) TRUE 10043 2006 Annual Stack Test 4

Flue 1 1 PM10 (Filterable) 1.83 milligramper cubic meter (mg/m3) FALSE 10043 2006 Annual Stack Test 4

Flue 1 2 PM10 (Filterable) 2.29 milligramper cubic meter (mg/m3) FALSE 10043 2006 Annual Stack Test 4

Flue 1 3 PM10 (Filterable) 1.83 milligramper cubic meter (mg/m3) FALSE

Page 65sampling_run_pollutants1

10043 2006 Annual Stack Test 5

Flue 1 1 Hydrogen Fluoride (HF) 0.03 parts per million by volume (dry) (ppmvd) TRUE 10043 2006 Annual Stack Test 5

Flue 1 2 Hydrogen Fluoride (HF) 0.03 parts per million by volume (dry) (ppmvd) TRUE 10043 2006 Annual Stack Test 5

Flue 1 3 Hydrogen Fluoride (HF) 0.03 parts per million by volume (dry) (ppmvd) TRUE 10043 2007 Annual Stack Test 1

Flue 1 1 Total Suspended Particulates (TSP) 10.3 milligramper cubic meter (mg/m3)

FALSE 10043 2007 Annual Stack Test 1

Flue 1 2 Total Suspended Particulates (TSP) 8.47 milligramper cubic meter (mg/m3)

FALSE 10043 2007 Annual Stack Test 1

Flue 1 3 Total Suspended Particulates (TSP) 10.07 milligramper cubic meter (mg/m3)

FALSE 10043 2007 Annual Stack Test 2

Flue 1 1 Hydrogen Fluoride (HF) 0.009 parts per million by volume (dry) (ppmvd) TRUE 10043 2007 Annual Stack Test 2

Flue 1 2 Hydrogen Fluoride (HF) 0.01 parts per million by volume (dry) (ppmvd) TRUE 10043 2007 Annual Stack Test 2

Flue 1 3 Hydrogen Fluoride (HF) 0.01 parts per million by volume (dry) (ppmvd) TRUE 10043 2007 Annual Stack Test 3

Flue 1 1 Hydrogen Chloride (HCl) 0.15 parts per million by volume (dry) (ppmvd) TRUE 10043 2007 Annual Stack Test 3

Flue 1 2 Hydrogen Chloride (HCl) 0.15 parts per million by volume (dry) (ppmvd) TRUE 10043 2007 Annual Stack Test 3

Flue 1 3 Hydrogen Chloride (HCl) 0.14 parts per million by volume (dry) (ppmvd) TRUE 10043 2007 Annual Stack Test 4

Flue 1 1 Arsenic (As) TRUE 10043 2007 Annual Stack Test 4

Flue 1 1 Beryllium(Be) TRUE 10043 2007 Annual Stack Test 4

Flue 1 1 Cadmium (Cd) FALSE 10043 2007 Annual Stack Test 4

Flue 1 1 Chromium (Cr) FALSE 10043 2007 Annual Stack Test 4

Flue 1 1 Cobalt (Co) TRUE 10043 2007 Annual Stack Test 4

Flue 1 1 Lead (Pb) FALSE 10043 2007 Annual Stack Test 4

Flue 1 1 Manganese (Mn) FALSE 10043 2007 Annual Stack Test 4

Flue 1 1 Nickel (Ni) FALSE 10043 2007 Annual Stack Test 4

Flue 1 1 Phosphorus (P) TRUE 10043 2007 Annual Stack Test 4

Flue 1 1 Selenium(Se) TRUE 10043 2007 Annual Stack Test 4

Flue 1 1 Total Mercury (Hgt) TRUE 10043 2007 Annual Stack Test 4

Flue 1 2 Arsenic (As) TRUE 10043 2007 Annual Stack Test 4

Flue 1 2 Beryllium(Be) TRUE 10043 2007 Annual Stack Test 4

Flue 1 2 Cadmium (Cd) FALSE 10043 2007 Annual Stack Test 4

Flue 1 2 Chromium (Cr) FALSE 10043 2007 Annual Stack Test 4

Flue 1 2 Cobalt (Co) TRUE 10043 2007 Annual Stack Test 4

Flue 1 2 Lead (Pb) TRUE 10043 2007 Annual Stack Test 4

Flue 1 2 Manganese (Mn) FALSE 10043 2007 Annual Stack Test 4

Flue 1 2 Nickel (Ni) FALSE 10043 2007 Annual Stack Test 4

Flue 1 2 Phosphorus (P) TRUE 10043 2007 Annual Stack Test 4

Flue 1 2 Selenium(Se) TRUE 10043 2007 Annual Stack Test 4

Flue 1 2 Total Mercury (Hgt) TRUE 10043 2007 Annual Stack Test 4

Flue 1 3 Arsenic (As) TRUE 10043 2007 Annual Stack Test 4

Flue 1 3 Beryllium(Be) TRUE 10043 2007 Annual Stack Test 4

Flue 1 3 Cadmium (Cd) FALSE 10043 2007 Annual Stack Test 4

Flue 1 3 Chromium (Cr) FALSE 10043 2007 Annual Stack Test 4

Flue 1 3 Cobalt (Co) TRUE 10043 2007 Annual Stack Test 4

Flue 1 3 Lead (Pb) FALSE 10043 2007 Annual Stack Test 4

Flue 1 3 Manganese (Mn) FALSE 10043 2007 Annual Stack Test 4

Flue 1 3 Phosphorus (P) TRUE 10043 2007 Annual Stack Test 4

Flue 1 3 Selenium(Se) TRUE 10043 2007 Annual Stack Test 4

Flue 1 3 Total Mercury (Hgt) TRUE 10043 2007 Annual Stack Test 5

Flue 1 1 PM10 (Filterable) 6.87 milligramper cubic meter (mg/m3) FALSE 10043 2007 Annual Stack Test 5

Flue 1 2 PM10 (Filterable) 6.87 milligramper cubic meter (mg/m3) FALSE 10043 2007 Annual Stack Test 5

Flue 1 3 PM10 (Filterable) 9.15 milligramper cubic meter (mg/m3) FALSE 10043 2007 Annual Stack Test 6

Flue 1 1 Benz(a)anthracene FALSE 10043 2007 Annual Stack Test 6

Flue 1 1 Benzo(a)pyrene TRUE 10043 2007 Annual Stack Test 6

Flue 1 1 Benzo(b)fluoranthene FALSE 10043 2007 Annual Stack Test 6

Flue 1 1 Benzo(k)fluoranthene TRUE 10043 2007 Annual Stack Test 6

Flue 1 1 Chrysene FALSE

Page 66sampling_run_pollutants1

10043 2007 Annual Stack Test 6

Flue 1 1 Dibenzo(a,h)anthracene TRUE 10043 2007 Annual Stack Test 6

Flue 1 1 Indeno(1,2,3-c,d)pyrene FALSE 10043 2007 Annual Stack Test 6

Flue 1 1 Polycyclic Organic Matter (POM) TRUE 10043 2007 Annual Stack Test 6

Flue 1 2 Benz(a)anthracene FALSE 10043 2007 Annual Stack Test 6

Flue 1 2 Benzo(a)pyrene TRUE 10043 2007 Annual Stack Test 6

Flue 1 2 Benzo(b)fluoranthene FALSE 10043 2007 Annual Stack Test 6

Flue 1 2 Benzo(k)fluoranthene FALSE 10043 2007 Annual Stack Test 6

Flue 1 2 Chrysene FALSE 10043 2007 Annual Stack Test 6

Flue 1 2 Dibenzo(a,h)anthracene TRUE 10043 2007 Annual Stack Test 6

Flue 1 2 Indeno(1,2,3-c,d)pyrene FALSE 10043 2007 Annual Stack Test 6

Flue 1 2 Polycyclic Organic Matter (POM) TRUE 10043 2007 Annual Stack Test 6

Flue 1 3 Benz(a)anthracene FALSE 10043 2007 Annual Stack Test 6

Flue 1 3 Benzo(a)pyrene TRUE 10043 2007 Annual Stack Test 6

Flue 1 3 Benzo(b)fluoranthene TRUE 10043 2007 Annual Stack Test 6

Flue 1 3 Benzo(k)fluoranthene TRUE 10043 2007 Annual Stack Test 6

Flue 1 3 Chrysene FALSE 10043 2007 Annual Stack Test 6

Flue 1 3 Dibenzo(a,h)anthracene TRUE 10043 2007 Annual Stack Test 6

Flue 1 3 Indeno(1,2,3-c,d)pyrene TRUE 10043 2007 Annual Stack Test 6

Flue 1 3 Polycyclic Organic Matter (POM) TRUE 10043 2006 Annual Stack Test 3

Flue 1 1 Chromium (Cr) TRUE 10043 2008 Annual Stack testing 1

Flue 1 1 Total Suspended Particulates (TSP) 5.72 milligramper cubic meter (mg/m3)

FALSE 10043 2008 Annual Stack testing 1

Flue 1 2 Total Suspended Particulates (TSP) 5.02 milligramper cubic meter (mg/m3)

FALSE 10043 2008 Annual Stack testing 1

Flue 1 3 Total Suspended Particulates (TSP) 5.26 milligramper cubic meter (mg/m3)

FALSE 10043 2008 Annual Stack Test 2

Flue 1 1 Hydrogen Fluoride (HF) 0.021 parts per million by volume (dry) (ppmvd) TRUE 10043 2008 Annual Stack Test 2

Flue 1 2 Hydrogen Fluoride (HF) 0.021 parts per million by volume (dry) (ppmvd) TRUE 0.021 10043 2008 Annual Stack Test 2

Flue 1 3 Hydrogen Fluoride (HF) 0.02 parts per million by volume (dry) (ppmvd) TRUE 10043 2008 Annual Stack Test 3

Flue 1 1 Hydrogen Chloride (HCl) 0.32 parts per million by volume (dry) (ppmvd) TRUE 10043 2008 Annual Stack Test 3

Flue 1 2 Hydrogen Chloride (HCl) 0.32 parts per million by volume (dry) (ppmvd) TRUE 10043 2008 Annual Stack Test 3

Flue 1 3 Hydrogen Chloride (HCl) 0.33 parts per million by volume (dry) (ppmvd) TRUE 10043 2008 Annual Stack Test 4

Flue 1 1 Arsenic (As) TRUE 10043 2008 Annual Stack Test 4

Flue 1 1 Beryllium(Be) TRUE 10043 2008 Annual Stack Test 4

Flue 1 1 Cadmium (Cd) FALSE 10043 2008 Annual Stack Test 4

Flue 1 1 Chromium (Cr) FALSE 10043 2008 Annual Stack Test 4

Flue 1 1 Cobalt (Co) TRUE 10043 2008 Annual Stack Test 4

Flue 1 1 Lead (Pb) FALSE 10043 2008 Annual Stack Test 4

Flue 1 1 Manganese (Mn) FALSE 10043 2008 Annual Stack Test 4

Flue 1 1 Nickel (Ni) FALSE 10043 2008 Annual Stack Test 4

Flue 1 1 Phosphorus (P) TRUE 10043 2008 Annual Stack Test 4

Flue 1 1 Selenium(Se) TRUE 10043 2008 Annual Stack Test 4

Flue 1 1 Total Mercury (Hgt) TRUE 10043 2008 Annual Stack Test 4

Flue 1 2 Arsenic (As) TRUE 10043 2008 Annual Stack Test 4

Flue 1 2 Beryllium(Be) TRUE 10043 2008 Annual Stack Test 4

Flue 1 2 Cadmium (Cd) FALSE 10043 2008 Annual Stack Test 4

Flue 1 2 Chromium (Cr) FALSE 10043 2008 Annual Stack Test 4

Flue 1 2 Cobalt (Co) TRUE 10043 2008 Annual Stack Test 4

Flue 1 2 Lead (Pb) FALSE 10043 2008 Annual Stack Test 4

Flue 1 2 Manganese (Mn) FALSE 10043 2008 Annual Stack Test 4

Flue 1 2 Nickel (Ni) FALSE 10043 2008 Annual Stack Test 4

Flue 1 2 Phosphorus (P) TRUE 10043 2008 Annual Stack Test 4

Flue 1 2 Selenium(Se) FALSE 10043 2008 Annual Stack Test 4

Flue 1 2 Total Mercury (Hgt) FALSE 10043 2008 Annual Stack Test 4

Flue 1 3 Arsenic (As) TRUE

Page 67sampling_run_pollutants1

10043 2008 Annual Stack Test 4

Flue 1 3 Beryllium(Be) TRUE 10043 2008 Annual Stack Test 4

Flue 1 3 Cadmium (Cd) FALSE 10043 2008 Annual Stack Test 4

Flue 1 3 Chromium (Cr) FALSE 10043 2008 Annual Stack Test 4

Flue 1 3 Cobalt (Co) TRUE 10043 2008 Annual Stack Test 4

Flue 1 3 Lead (Pb) FALSE 10043 2008 Annual Stack Test 4

Flue 1 3 Manganese (Mn) FALSE 10043 2008 Annual Stack Test 4

Flue 1 3 Nickel (Ni) FALSE 10043 2008 Annual Stack Test 4

Flue 1 3 Phosphorus (P) TRUE 10043 2008 Annual Stack Test 4

Flue 1 3 Selenium(Se) TRUE 10043 2008 Annual Stack Test 4

Flue 1 3 Total Mercury (Hgt) TRUE 10043 2008 Stack Test 5

Flue 1 1 PM10 (Filterable) 9.15 milligramper cubic meter (mg/m3) FALSE 10043 2008 Stack Test 5

Flue 1 2 PM10 (Filterable) 9.15 milligramper cubic meter (mg/m3) FALSE 10043 2008 Stack Test 5

Flue 1 3 PM10 (Filterable) 6.87 milligramper cubic meter (mg/m3) FALSE 10043 2009 Annual Stack Test 1

Flue 1 1 Total Suspended Particulates (TSP) 6.87 milligramper cubic meter (mg/m3)

FALSE 10043 2009 Annual Stack Test 1

Flue 1 2 Total Suspended Particulates (TSP) 4.58 milligramper cubic meter (mg/m3)

FALSE 10043 2009 Annual Stack Test 1

Flue 1 3 Total Suspended Particulates (TSP) 4.58 milligramper cubic meter (mg/m3)

FALSE 10043 2009 Annual Stack Test 2

Flue 1 1 Hydrogen Fluoride (HF) 0.01 parts per million by volume (dry) (ppmvd) TRUE 10043 2009 Annual Stack Test 2

Flue 1 2 Hydrogen Fluoride (HF) 0.01 parts per million by volume (dry) (ppmvd) TRUE 10043 2009 Annual Stack Test 2

Flue 1 3 Hydrogen Fluoride (HF) 0.01 parts per million by volume (dry) (ppmvd) TRUE 10043 2009 Annual Stack Test 3

Flue 1 1 Hydrogen Chloride (HCl) 0.06 parts per million by volume (dry) (ppmvd) TRUE 10043 2009 Annual Stack Test 3

Flue 1 2 Hydrogen Chloride (HCl) 0.06 parts per million by volume (dry) (ppmvd) TRUE 10043 2009 Annual Stack Test 3

Flue 1 3 Hydrogen Chloride (HCl) 0.06 parts per million by volume (dry) (ppmvd) TRUE 10043 2009 Annual Stack Test 4

Flue 1 1 Arsenic (As) FALSE 10043 2009 Annual Stack Test 4

Flue 1 1 Beryllium(Be) FALSE 10043 2009 Annual Stack Test 4

Flue 1 1 Cadmium (Cd) FALSE 10043 2009 Annual Stack Test 4

Flue 1 1 Chromium (Cr) FALSE 10043 2009 Annual Stack Test 4

Flue 1 1 Cobalt (Co) FALSE 10043 2009 Annual Stack Test 4

Flue 1 1 Lead (Pb) FALSE 10043 2009 Annual Stack Test 4

Flue 1 1 Manganese (Mn) FALSE 10043 2009 Annual Stack Test 4

Flue 1 1 Nickel (Ni) FALSE 10043 2009 Annual Stack Test 4

Flue 1 1 Phosphorus (P) FALSE 10043 2009 Annual Stack Test 4

Flue 1 1 Selenium(Se) TRUE 10043 2009 Annual Stack Test 4

Flue 1 1 Total Mercury (Hgt) FALSE 10043 2009 Annual Stack Test 4

Flue 1 2 Arsenic (As) FALSE 10043 2009 Annual Stack Test 4

Flue 1 2 Beryllium(Be) FALSE 10043 2009 Annual Stack Test 4

Flue 1 2 Cadmium (Cd) FALSE 10043 2009 Annual Stack Test 4

Flue 1 2 Chromium (Cr) FALSE 10043 2009 Annual Stack Test 4

Flue 1 2 Cobalt (Co) FALSE 10043 2009 Annual Stack Test 4

Flue 1 2 Lead (Pb) FALSE 10043 2009 Annual Stack Test 4

Flue 1 2 Manganese (Mn) FALSE 10043 2009 Annual Stack Test 4

Flue 1 2 Nickel (Ni) FALSE 10043 2009 Annual Stack Test 4

Flue 1 2 Phosphorus (P) FALSE 10043 2009 Annual Stack Test 4

Flue 1 2 Selenium(Se) FALSE 10043 2009 Annual Stack Test 4

Flue 1 2 Total Mercury (Hgt) FALSE 10043 2009 Annual Stack Test 4

Flue 1 3 Arsenic (As) FALSE 10043 2009 Annual Stack Test 4

Flue 1 3 Beryllium(Be) FALSE 10043 2009 Annual Stack Test 4

Flue 1 3 Cadmium (Cd) FALSE 10043 2009 Annual Stack Test 4

Flue 1 3 Chromium (Cr) FALSE 10043 2009 Annual Stack Test 4

Flue 1 3 Cobalt (Co) FALSE 10043 2009 Annual Stack Test 4

Flue 1 3 Lead (Pb) FALSE 10043 2009 Annual Stack Test 4

Flue 1 3 Manganese (Mn) FALSE 10043 2009 Annual Stack Test 4

Flue 1 3 Nickel (Ni) FALSE

Page 68sampling_run_pollutants1

10043 2009 Annual Stack Test 4

Flue 1 3 Phosphorus (P) FALSE 10043 2009 Annual Stack Test 4

Flue 1 3 Selenium(Se) FALSE 10043 2009 Annual Stack Test 4

Flue 1 3 Total Mercury (Hgt) FALSE 10043 2009 Annual Stack Test 5

Flue 1 1 PM10 (Filterable) 34.04 milligramper cubic meter (mg/m3)

FALSE 10043 2009 Annual Stack Test 5

Flue 1 2 PM10 (Filterable) 9.15 milligramper cubic meter (mg/m3) FALSE 10043 2009 Annual Stack Test 5

Flue 1 3 PM10 (Filterable) 11.44 milligramper cubic meter (mg/m3)

FALSE

Page 69sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment 29.1 pound per hour (lb/hr)

FALSE 0.0124 pound per million British Thermal Unit (lb/MMBtu) FALSE 23.5 pound per hour (lb/hr)

FALSE 0.0101 pound per million British Thermal Unit (lb/MMBtu) FALSE 18.4 pound per hour (lb/hr)

FALSE 0.0081 pound per million British Thermal Unit (lb/MMBtu) FALSE 26.8 pound per hour (lb/hr)

FALSE 0.018 pound per million British Thermal Unit (lb/MMBtu) FALSE 17.7 pound per hour (lb/hr)

FALSE 0.007 pound per million British Thermal Unit (lb/MMBtu) FALSE 27.9 pound per hour (lb/hr)

FALSE 0.012 pound per million British Thermal Unit (lb/MMBtu) FALSE 18.9 pound per hour (lb/hr)

FALSE 0.008 pound per million British Thermal Unit (lb/MMBtu) FALSE 328 pound per hour (lb/hr)

FALSE 0.134 pound per million British Thermal Unit (lb/MMBtu) FALSE 156.8 pound per hour (lb/hr)

FALSE 0.0642 pound per million British Thermal Unit (lb/MMBtu) FALSE 265.2 pound per hour (lb/hr)

FALSE 0.109 pound per million British Thermal Unit (lb/MMBtu) FALSE 2.67 pound per hour (lb/hr)

FALSE 0.00109 pound per million British Thermal Unit (lb/MMBtu) FALSE 328.4 pound per hour (lb/hr)

FALSE 0.131 pound per million British Thermal Unit (lb/MMBtu) FALSE 111 pound per hour (lb/hr)

FALSE 0.0444 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.14 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.14 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.36 pound per hour (lb/hr)

FALSE 0.00016 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.1 pound per hour (lb/hr)

TRUE 0.1 FALSE < the limit of detection 0.3 pound per hour (lb/hr)

TRUE TRUE 0.5 pound per hour (lb/hr)

FALSE 0.0002 pound per million British Thermal Unit (lb/MMBtu) FALSE 10 pound per hour (lb/hr)

FALSE FALSE 13.31 pound per hour (lb/hr)

FALSE FALSE 20.06 pound per hour (lb/hr)

FALSE FALSE 1.47 pound per hour (lb/hr)

TRUE TRUE < limit of detection 1.67 pound per hour (lb/hr)

TRUE TRUE < Limit of detection 1.35 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0008 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.000051 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.00008 pound per hour (lb/hr)

FALSE FALSE 0.0016 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0008 pound per hour (lb/hr)

TRUE 0.0008 TRUE < limit of detection 0.00073 pound per hour (lb/hr)

FALSE FALSE 0.0022 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.016 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.016 pound per hour (lb/hr)

FALSE FALSE 0.0031 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.00088 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.000056 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.000088 pound per hour (lb/hr) FALSE FALSE 0.0067 pound per hour (lb/hr)

FALSE FALSE 0.0018 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.00096 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.0099 pound per hour (lb/hr)

FALSE FALSE 0.0019 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.027 pound per hour (lb/hr)

TRUE TRUE < Limit of detection 292.1 pound per hour (lb/hr)

FALSE 0.117 pound per million British Thermal Unit (lb/MMBtu) FALSE 3.98 pound per hour (lb/hr)

FALSE 0.00159 pound per million British Thermal Unit (lb/MMBtu) FALSE 351.8 pound per hour (lb/hr)

FALSE 0.146 pound per million British Thermal Unit (lb/MMBtu) FALSE 198.4 pound per hour (lb/hr)

FALSE 0.0823 pound per million British Thermal Unit (lb/MMBtu) FALSE 232.1 pound per hour (lb/hr)

FALSE 0.096 pound per million British Thermal Unit (lb/MMBtu) FALSE 1.51 pound per hour (lb/hr)

FALSE 0.00063 pound per million British Thermal Unit (lb/MMBtu) FALSE 359.9 pound per hour (lb/hr)

FALSE 0.148 pound per million British Thermal Unit (lb/MMBtu) FALSE

Page 70sampling_run_pollutants1

100 pound per hour (lb/hr)

FALSE 0.0412 pound per million British Thermal Unit (lb/MMBtu) FALSE 249 pound per hour (lb/hr)

FALSE 0.103 pound per million British Thermal Unit (lb/MMBtu) FALSE 1.29 pound per hour (lb/hr)

FALSE 0.00053 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.9197 pound per hour (lb/hr)

FALSE 0.00041 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.00055 pound per hour (lb/hr)

FALSE 2.4E-07 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0018 pound per hour (lb/hr)

FALSE 7.9E-07 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.1061 pound per hour (lb/hr)

FALSE 0.000047 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0049 pound per hour (lb/hr)

FALSE 2.1E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.1088 pound per hour (lb/hr)

FALSE 4.84E-05 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.1195 pound per hour (lb/hr)

FALSE 0.000053 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0017 pound per hour (lb/hr)

TRUE TRUE < Less than the limit of detection 0.0842 pound per hour (lb/hr)

FALSE 0.000037 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0007 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0055 pound per hour (lb/hr)

FALSE 2.43E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.7894 pound per hour (lb/hr)

FALSE 0.00036 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.00041 pound per hour (lb/hr)

FALSE 1.9E-07 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0014 pound per hour (lb/hr)

FALSE 6.21E-07 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0314 pound per hour (lb/hr)

FALSE 1.43E-05 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0094 pound per hour (lb/hr)

FALSE 1.55E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0922 pound per hour (lb/hr)

FALSE 0.000042 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0856 pound per hour (lb/hr)

FALSE 0.000039 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0017 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0284 pound per hour (lb/hr)

FALSE 1.29E-05 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0007 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0027 pound per hour (lb/hr)

FALSE 1.24E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.8217 pound per hour (lb/hr)

FALSE 0.00036 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.00041 pound per hour (lb/hr)

FALSE 1.9E-07 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0015 pound per hour (lb/hr)

FALSE 6.8E-07 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0183 pound per hour (lb/hr)

FALSE 8.09E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0027 pound per hour (lb/hr)

FALSE 1.17E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0949 pound per hour (lb/hr)

FALSE 4.19E-05 pound per million British Thermal Unit (lb/MMBtu) FALSE 1.0862 pound per hour (lb/hr)

FALSE 0.000479 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.002 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0165 pound per hour (lb/hr)

FALSE 7.2E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0007 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0056 pound per hour (lb/hr)

FALSE 2.47E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.018 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0032 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.00091 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.000058 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.00005 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.0021 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0018 pound per hour (lb/hr)

TRUE TRUE Lim it of detection 0.00091 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.0066 pound per hour (lb/hr)

FALSE FALSE 0.0021 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.02 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.003 pound per hour (lb/hr)

FALSE FALSE 0.0033 pound per hour (lb/hr)

TRUE TRUE < limit of detection 3.75 pound per hour (lb/hr)

FALSE FALSE 4.71 pound per hour (lb/hr)

FALSE FALSE 3.74 pound per hour (lb/hr)

FALSE FALSE

Page 71sampling_run_pollutants1

0.04 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.04 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.04 pound per hour (lb/hr)

TRUE TRUE < limit of detection 20.52 pound per hour (lb/hr)

FALSE 0.0009 pound per million British Thermal Unit (lb/MMBtu) FALSE 16.46 pound per hour (lb/hr)

FALSE 0.007 pound per million British Thermal Unit (lb/MMBtu) FALSE 20.04 pound per hour (lb/hr)

FALSE 0.008 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.015 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.017 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.015 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.46 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.43 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.41 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.00098 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.000045 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.00025 pound per hour (lb/hr)

FALSE FALSE 0.0094 pound per hour (lb/hr)

FALSE FALSE 0.0021 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.002 pound per hour (lb/hr)

FALSE FALSE 0.0073 pound per hour (lb/hr)

FALSE FALSE 0.014 pound per hour (lb/hr)

FALSE FALSE 0.021 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0036 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0019 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.00099 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.000044 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.00016 pound per hour (lb/hr)

FALSE FALSE 0.0092 pound per hour (lb/hr)

FALSE FALSE 0.0028 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0012 pound per hour (lb/hr)

TRUE TRUE < limit 0f detection 0.0039 pound per hour (lb/hr)

FALSE FALSE 0.0075 pound per hour (lb/hr)

FALSE FALSE 0.02 pound per hour (lb/hr)

TRUE 0.02 TRUE < limit of detection 0.002 pound per hour (lb/hr)

TRUE 0.002 TRUE < limit of detection 0.0014 pound per hour (lb/hr)

TRUE 0.0014 TRUE < limit of detection 0.001 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.000047 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.00027 pound per hour (lb/hr)

FALSE FALSE 0.0075 pound per hour (lb/hr)

FALSE FALSE 0.0021 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0016 pound per hour (lb/hr)

FALSE FALSE 0.0058 pound per hour (lb/hr)

FALSE FALSE 0.023 pound per hour (lb/hr)

TRUE TRUE < Limit of detection 0.0021 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0014 pound per hour (lb/hr)

TRUE TRUE < limit of detection 14.42 pound per hour (lb/hr)

FALSE 0.006 pound per million British Thermal Unit (lb/MMBtu) FALSE 14.05 pound per hour (lb/hr)

FALSE 0.006 pound per million British Thermal Unit (lb/MMBtu) FALSE 17 pound per hour (lb/hr)

FALSE 0.007 pound per million British Thermal Unit (lb/MMBtu) FALSE 3.7E-07 pound per hour (lb/hr)

FALSE FALSE 1.5E-06 pound per hour (lb/hr)

TRUE TRUE < limit of detection 4.8E-07 pound per hour (lb/hr)

FALSE FALSE 7.6E-07 pound per hour (lb/hr)

TRUE TRUE < limit of detection 7.2E-07 pound per hour (lb/hr)

FALSE FALSE

Page 72sampling_run_pollutants1

1.8E-06 pound per hour (lb/hr)

TRUE TRUE < limit of detection 7.3E-07 pound per hour (lb/hr)

FALSE FALSE 6.4E-06 pound per hour (lb/hr)

TRUE TRUE < limit of detection 3.2E-07 pound per hour (lb/hr)

FALSE FALSE 1.5E-06 pound per hour (lb/hr)

TRUE TRUE < limit of detection 5.6E-07 pound per hour (lb/hr)

FALSE FALSE 1.5E-07 pound per hour (lb/hr)

FALSE FALSE 8.6E-07 pound per hour (lb/hr)

FALSE FALSE 1.8E-06 pound per hour (lb/hr)

TRUE TRUE < limit of detection 3.3E-07 pound per hour (lb/hr)

FALSE FALSE 5.5E-06 pound per hour (lb/hr)

TRUE TRUE < limit of detection 7.6E-07 pound per hour (lb/hr)

FALSE FALSE 1.5E-06 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.000003 pound per hour (lb/hr) TRUE TRUE < limit of detection 7.7E-07 pound per hour (lb/hr)

TRUE TRUE < limit of detection 9.9E-07 pound per hour (lb/hr)

FALSE FALSE 1.8E-06 pound per hour (lb/hr)

TRUE TRUE < limit of detection 1.7E-06 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.000011 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.0045 pound per hour (lb/hr)

TRUE TRUE < limit of detection 11.04 pound per hour (lb/hr)

FALSE 0.005 pound per million British Thermal Unit (lb/MMBtu) FALSE 10.04 pound per hour (lb/hr)

FALSE 0.004 pound per million British Thermal Unit (lb/MMBtu) FALSE 10.39 pound per hour (lb/hr)

FALSE 0.004 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.035 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.035 pound per hour (lb/hr)

TRUE 0.035 TRUE < limit of detection 0.033 pound per hour (lb/hr)

TRUE FALSE < limit of detection 1.01 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.99 pound per hour (lb/hr)

TRUE TRUE < limit of detection 1.02 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0006 pound per hour (lb/hr)

TRUE 0.0006 TRUE < limit of detection 0.00006 pound per hour (lb/hr) TRUE 0.00006 TRUE < limit of detection 0.00038 pound per hour (lb/hr)

FALSE FALSE 0.0038 pound per hour (lb/hr)

FALSE FALSE 0.0014 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0027 pound per hour (lb/hr)

FALSE FALSE 0.0034 pound per hour (lb/hr)

FALSE FALSE 0.0059 pound per hour (lb/hr)

FALSE FALSE 0.12 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.004 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0006 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.00077 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.00006 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.00038 pound per hour (lb/hr)

FALSE FALSE 0.0071 pound per hour (lb/hr)

FALSE FALSE 0.0013 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0043 pound per hour (lb/hr)

FALSE FALSE 0.0023 pound per hour (lb/hr)

FALSE FALSE 0.0044 pound per hour (lb/hr)

FALSE FALSE 0.012 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0047 pound per hour (lb/hr)

FALSE FALSE 0.0006 pound per hour (lb/hr)

FALSE FALSE 0.00066 pound per hour (lb/hr) TRUE TRUE < limit of detection

Page 73sampling_run_pollutants1

0.000066 pound per hour (lb/hr) TRUE TRUE < limit of detection 0.00028 pound per hour (lb/hr)

FALSE FALSE 0.0041 pound per hour (lb/hr)

FALSE FALSE 0.0012 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0033 pound per hour (lb/hr)

FALSE FALSE 0.0028 pound per hour (lb/hr)

FALSE FALSE 0.0039 pound per hour (lb/hr)

FALSE FALSE 0.12 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0038 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.0006 pound per hour (lb/hr)

TRUE TRUE < limit of detection 17.14 pound per hour (lb/hr)

FALSE 0.007 pound per million British Thermal Unit (lb/MMBtu) FALSE 17.13 pound per hour (lb/hr)

FALSE 0.007 pound per million British Thermal Unit (lb/MMBtu) FALSE 15.88 pound per hour (lb/hr)

FALSE 0.006 pound per million British Thermal Unit (lb/MMBtu) FALSE 12.99 pound per hour (lb/hr)

FALSE 0.006 pound per million British Thermal Unit (lb/MMBtu) FALSE 10.71 pound per hour (lb/hr)

FALSE 0.005 pound per million British Thermal Unit (lb/MMBtu) FALSE 7.72 pound per hour (lb/hr)

FALSE 0.004 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.02 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.02 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.02 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.17 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.17 pound per hour (lb/hr)

TRUE TRUE < less than the limit of detection 0.17 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.00038 pound per hour (lb/hr)

FALSE FALSE 0.000024 pound per hour (lb/hr) FALSE FALSE 0.00016 pound per hour (lb/hr)

FALSE FALSE 0.0016 pound per hour (lb/hr)

FALSE FALSE 0.00014 pound per hour (lb/hr)

FALSE FALSE 0.0016 pound per hour (lb/hr)

FALSE FALSE 0.001 pound per hour (lb/hr)

FALSE FALSE 0.0016 pound per hour (lb/hr)

FALSE FALSE 0.0061 pound per hour (lb/hr)

FALSE FALSE 0.0001 pound per hour (lb/hr)

TRUE TRUE < limit of detection 0.000025 pound per hour (lb/hr) FALSE FALSE 0.00043 pound per hour (lb/hr)

FALSE FALSE 0.000022 pound per hour (lb/hr) FALSE FALSE 0.000082 pound per hour (lb/hr) FALSE FALSE 0.0014 pound per hour (lb/hr)

FALSE FALSE 0.00035 pound per hour (lb/hr)

FALSE FALSE 0.0022 pound per hour (lb/hr)

FALSE FALSE 0.00084 pound per hour (lb/hr)

FALSE FALSE 0.0025 pound per hour (lb/hr)

FALSE FALSE 0.0044 pound per hour (lb/hr)

FALSE FALSE 0.0012 pound per hour (lb/hr)

FALSE FALSE 0.000038 pound per hour (lb/hr) FALSE FALSE 0.00036 pound per hour (lb/hr)

FALSE FALSE 0.000019 pound per hour (lb/hr) FALSE FALSE 0.00011 pound per hour (lb/hr)

FALSE FALSE 0.0016 pound per hour (lb/hr)

FALSE FALSE 0.00027 pound per hour (lb/hr)

FALSE FALSE 0.0024 pound per hour (lb/hr)

FALSE FALSE 0.001 pound per hour (lb/hr)

FALSE FALSE 0.0032 pound per hour (lb/hr)

FALSE FALSE

Page 74sampling_run_pollutants1

0.0046 pound per hour (lb/hr)

FALSE FALSE 0.000074 pound per hour (lb/hr) FALSE FALSE 0.000035 pound per hour (lb/hr) FALSE FALSE 65.62 pound per hour (lb/hr)

FALSE 0.027 pound per million British Thermal Unit (lb/MMBtu) FALSE 20.23 pound per hour (lb/hr)

FALSE 0.008 pound per million British Thermal Unit (lb/MMBtu) FALSE 25.73 pound per hour (lb/hr)

FALSE 0.011 pound per million British Thermal Unit (lb/MMBtu) FALSE

Page 75sampling_run_pollutants1

run_pollutant_comment

< lim it of detection < lim it of detection

< the limit of detection

< lim it of detection < Limit of detection < lim it of detection < lim it of detection < lim it of detection

< lim it of detection < lim it of detection

< lim it of detection < lim it of detection

< lim it of detection < lim it of detection < lim it of detection

< lim it of detection < lim it of detection

< lim it of detection < Limit of detection

Page 76sampling_run_pollutants1

< Less than the limit of detection

< lim it of detection

< lim it of detection

< lim it of detection

< lim it of detection

< lim it of detection

< lim it of detection < lim it of detection < lim it of detection < lim it of detection < lim it of detection < lim it of detection Lim it of detection < lim it of detection

< lim it of detection < lim it of detection

< lim it of detection

Page 77sampling_run_pollutants1

< lim it of detection < lim it of detection < lim it of detection

< lim it of detection < lim it of detection < lim it of detection < lim it of detection < lim it of detection < lim it of detection < lim it of detection < lim it of detection

< lim it of detection

< lim it of detection < lim it of detection < lim it of detection < lim it of detection < lim it of detection

< lim it of detection < lim it 0f detection

< lim it of detection < lim it of detection < lim it of detection < lim it of detection < lim it of detection

< lim it of detection

< Limit of detection < lim it of detection < lim it of detection

< lim it of detection

< lim it of detection

Page 78sampling_run_pollutants1

< lim it of detection

< lim it of detection

< lim it of detection

< lim it of detection

< lim it of detection

< lim it of detection < lim it of detection < lim it of detection

< lim it of detection < lim it of detection < lim it of detection < lim it of detection

< lim it of detection < lim it of detection < lim it of detection < lim it of detection < lim it of detection < lim it of detection < lim it of detection < lim it of detection

< lim it of detection

< lim it of detection < lim it of detection < lim it of detection < lim it of detection < lim it of detection

< lim it of detection

< lim it of detection

< lim it of detection

Page 79sampling_run_pollutants1

< lim it of detection

< lim it of detection

< lim it of detection < lim it of detection < lim it of detection

< lim it of detection < lim it of detection < lim it of detection < lim it of detection < less than the limit of detection < lim it of detection

< lim it of detection

Page 80sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL

Page 81sampling_run_fuel

fuel_conc_MDL

Page 82