### 1: Follow OEM recommendations when performing any retrofit & change to an approved filter drier. 2: When changing to POE, reduce contamination of old oil to less than 5%. 3: Forane® 

### 409A is recommended for most R-12 & R-500 systems. Use Forane® 

### 134a for automotive A/C and flooded evaporators. 4: Use 80% for cap tubes, 85-90% for TXVs. 5: Use PAG in automotive A/C only. 6: Forane® 

### 408A is recommended for R-502 applications. 7: For R-22 retrofits, use Forane® 

### 404A/507 for low temp and Forane® 

### 407C for A/C. RECOMMENDED OIL CHANGE RETROFIT CYLINDER SUCTION DISCHARGE DISCHARGE RETROFIT REQUIREMENTS2 

### CHARGE CHARGING PRESSURE PRESSURE TEMPERATURE APPLICATIONS1 

### WEIGHTS PHASE DIFFERENCE DIFFERENCE DIFFERENCE

R-12 & R-500 3 

### If Evaporator Temp. Use 80-90%4 

### Liquid Phase 0-5 PSI 15-25 PSI 5-25°F

Equipment >0°F, No Oil Change Charge Weight Only Higher than Higher than Higher than Required. If <0°F, of R-12/R-500 R-12 R-12 R-12 Do Partial (30%) Oil Change to AB

R-12 & R-5003 

### POE/PAG5 

### Use 90-95% Liquid or Vapor 1-3 PSI 5-15 PSI 0-10°F

Equipment Oil Change Charge Weight Phase Lower than Higher than Lower than Required of R-12/R-500 R-12 R-12 R-12

R-502 No Oil Change Use 85-90% Liquid Phase 1-3 PSI 0-5 PSI 10-35°F Equipment Required Charge Weight Only Lower than Higher than Higher than of R-502 R-502 R-502 R-502

R-5026 

### & R-22 7 

### POE Use 85-90% Liquid Phase 0-5 PSI 15-25 PSI 0-10°F

Equipment Oil Change Charge Weight Only Higher than Higher than Lower than Required of R-502 R-502 R-502 R-502

R-5026 

### & R-22 7 

### POE Use 85-90% Liquid Phase 0-5 PSI 20-35 PSI 0-10°F

Equipment Oil Change Charge Weight Only Higher than Higher than Lower than Required of R-502 R-502 R-502 R-502

R-22 7 

### POE Use 90-95% Liquid Phase Same as 15-25 PSI 10-15°F Equipment Oil Change Charge Weight Only R-22 Higher than Lower than Required of R-22 R-22 R-22 

# RETROFITTING WITH

QUICK REFERENCE GUIDE

www.forane-us.com
Technical Support (800) 738-7695

Customer Service (800) 245-5858 Values listed are general guidelines only. Actual system performance/requirements may vary.The statements, technical information and recommendations contained herein are believed to be accurate as of the date hereof. Since the conditions and methods of use of the product and of the information referred to herein are beyond our control, Arkema Inc. expressly disclaims any and all liability as to any resu lts obtained or arising from any use of the product or reliance on such information; NO WARRANTY OF FITNESS FOR ANY PARTICULAR PURPOSE, WARRANTY OF MERCHANTABILITY, OR ANY OTHER WARRANTY, EXPRESS OR IMPLIED, IS MADE CONCERNING THE GOODS DESCRIBED OR THE INFORMATION PROVIDED HEREIN. The information provided herein relates only to the specific product designated and may not be applicable when such product is used in combination with other materials or in any process. The user should thoroughly test any application before commercialization. Nothing contained herein should be construed as an inducement to infringe any patent, and the user is advised to take appropriate steps to be sure that any proposed use of the product will not result in patent infringement.

See MSDS for Health & Safety Considerations

.

Arkema Inc. 2000 Market Street, Philadelphia, PA 19103-3222 Tel.: 215-419-7000 www.Arkema-Inc.com Printed in USA **Sat. Temp**  **(°F)** R-407C R-407C R-410A Liquid Vapor Liquid Pressure Pressure Pressure

-50 15.4 18.7 12.4 17.2 13.5 17.9 12.2 16.8 -45 13.3 16.9 9.7 15.2 11.1 16.0 9.6 14.7 -40 11.0 14.8 6.8 13.1 8.4 13.8 6.7 12.4 -35 8.4 12.5 3.5 10.7 5.3 11.4 3.4 9.7 -30 5.5 9.8 0.0 8.1 2.0 8.7 0.1 6.8 -25 2.3 6.9 2.0 5.1 0.8 5.6 2.0 3.5

-20 0.6 3.7 4.1 1.9 2.9 2.2 4.1 0.1 -15 2.4 0.1 6.5 0.8 5.1 0.7 6.5 2.0 -10 4.5 1.9 9.0 2.8 7.5 2.8 9.1 4.2 -5 6.7 4.1 11.8 4.9 10.1 5.0 11.9 6.6 0 9.1 6.5 14.8 7.2 13.0 7.4 14.9 9.2 5 11.8 9.1 18.1 9.7 16.1 10.1 18.2 12.1

10 14.6 11.9 21.7 12.5 19.5 13.0 21.8 15.2 15 17.7 15.0 25.5 15.4 23.1 16.2 25.7 18.6 20 21.0 18.4 29.6 18.7 27.1 19.6 29.9 22.3 25 24.6 22.1 34.0 22.2 31.4 23.4 34.4 26.3 30 28.4 26.0 38.7 26.0 36.0 27.4 39.3 30.6 35 32.5 30.3 43.8 30.1 40.9 31.8 44.5 35.2

40 36.9 35.0 49.2 34.5 46.2 36.5 50.1 40.2 45 41.6 40.0 54.9 39.2 51.8 41.6 56.0 45.6 50 46.7 45.4 61.0 44.3 57.9 47.0 62.4 51.4 55 52.0 51.1 67.6 49.8 64.3 52.8 69.2 57.5 60 57.7 57.3 74.5 55.6 71.2 59.0 76.5 64.1 65 63.7 63.9 81.8 61.9 78.5 65.7 84.2 71.2

70 70.2 71.0 89.5 68.6 86.3 72.8 92.3 78.7 75 76.9 78.6 97.7 75.8 94.5 80.3 101.0 86.7 80 84.1 86.6 106.4 83.4 103.2 88.4 110.2 95.2 85 91.7 95.1 115.5 91.5 112.4 96.9 119.8 104.2 90 99.7 104.2 125.2 100.2 122.2 106.0 130.1 113.8 95 108.2 113.8 135.3 109.4 132.5 115.6 140.9 123.9

100 117.1 124.1 146.0 119.2 143.3 125.7 152.3 134.7 105 126.5 134.9 157.2 129.6 154.8 136.5 164.3 146.0 110 136.4 146.3 169.0 140.6 166.8 147.8 176.9 158.0 115 146.7 158.4 181.4 152.3 179.4 159.8 190.1 170.6 120 157.6 171.1 194.4 164.7 192.7 172.4 204.0 183.9 125 169.0 184.5 208.0 177.8 206.6 185.7 218.6 197.9

130 180.9 198.7 222.3 191.6 221.2 199.7 233.9 212.6 135 193.5 213.6 237.2 206.3 236.5 214.5 250.0 228.1 140 206.5 229.3 252.9 221.8 252.5 229.9 266.7 244.3 145 220.2 245.7 269.3 238.2 269.3 246.2 284.3 261.4 150 234.5 263.0 286.4 255.5 286.8 263.2 302.6 279.3 R-409A R-409A R-401A R-401A R-401B R-401B R-12 R-134a Liquid Vapor Liquid Vapor Liquid Vapor Pressure Pressure Pressure Pressure Pressure Pressure

Red Numerals - Inches Hg. Below 1 ATM Red Numerals - Inches Hg. Below 1 ATM Red Numerals - Inches Hg. Below 1 ATM **Sat. Temp**  **(°F)** PRESSURE (PSIG) PRESSURE (PSIG)

**Sat.** R-408A R-402A R-402B R-404A **Temp** R-502 Liquid Liquid Liquid Liquid R-507 **(°F)** Pressure Pressure Pressure Pressure R-22 R-11 R-123

-50 6.2 2.9 11.4 5.3 28.9 29.2 -45 2.7 0.4 8.5 8.0 28.7 29.0 -40 0.5 2.5 5.2 11.0 28.4 28.9 -35 2.6 4.8 1.5 14.2 28.1 28.7 -30 4.9 7.3 1.3 17.8 27.8 28.4 -25 7.4 10.1 3.6 21.8 27.4 28.1
-20 10.1 13.1 6.1 26.1 27.0 27.8 -15 13.2 16.5 8.8 30.8 26.5 27.4 -10 16.5 20.1 11.9 35.9 26.0 27.0 -5 20.0 24.0 15.2 41.5 25.4 26.5 0 23.9 28.3 18.9 47.5 24.7 25.9 5 28.2 33.0 22.9 54.1 23.9 25.3
10 32.8 38.0 27.3 61.2 23.1 24.6 15 37.7 43.5 32.0 68.8 22.1 23.7 20 43.0 49.3 37.2 77.1 21.1 22.8 25 48.7 55.7 42.7 86.0 19.9 21.8 30 54.9 62.5 48.7 95.5 18.6 20.7 35 61.5 69.8 55.2 105.7 17.2 19.5
40 68.5 77.6 62.1 116.6 15.6 18.1 45 76.0 86.0 69.5 128.3 13.9 16.6 50 84.0 94.9 77.5 140.8 12.0 15.0 55 92.5 104.5 86.0 154.1 10.0 13.1 60 101.6 114.6 95.1 168.2 7.8 11.2 65 111.2 125.4 104.8 183.2 5.4 9.0
70 121.4 136.9 115.2 199.2 2.7 6.6 75 132.2 149.1 126.2 216.1 0.0 4.0 80 143.6 162.1 137.8 234.0 1.5 1.2 85 155.7 175.8 150.2 253.0 3.2 0.9 90 168.4 190.2 163.4 273.0 4.9 2.5 95 181.8 205.5 177.4 294.1 6.8 4.2
100 195.9 221.6 192.1 316.4 8.8 6.1 105 210.7 238.5 207.8 339.9 10.9 8.1 110 226.3 256.4 224.4 364.6 13.2 10.3 115 242.7 275.1 241.9 390.5 15.6 12.6 120 259.9 294.7 260.5 417.7 18.3 15.1 125 277.9 315.2 280.1 446.3 21.0 17.7
130 296.8 336.7 300.9 476.3 24.0 20.6 135 316.5 359.2 322.9 507.6 27.1 23.6 140 337.2 382.6 346.2 540.5 30.4 26.8 145 358.8 407.0 370.8 574.8 34.0 30.2 150 381.5 432.4 396.9 610.6 37.7 33.8 -50 0.2 1.6 2.7 1.2 0.6 1.1 -45 1.9 1.1 5.1 3.3 2.7 3.3 -40 4.1 3.3 7.6 5.7 5.0 5.7 -35 6.5 5.6 10.5 8.3 7.6 8.3 -30 9.2 8.2 13.6 11.2 10.4 11.2 -25 12.1 11.0 17.0 14.4 13.4 14.3
-20 15.3 14.1 20.7 17.8 16.8 17.8 -15 18.8 17.5 24.7 21.5 20.5 21.6 -10 22.6 21.2 29.1 25.6 24.5 25.7 -5 26.7 25.2 33.9 30.0 28.8 30.1 0 31.1 29.5 39.0 34.8 33.5 34.9 5 35.9 34.2 44.5 40.0 38.6 40.2
10 41.0 39.3 50.5 45.5 44.0 45.8 15 46.5 44.8 56.9 51.5 49.9 51.8 20 52.5 50.7 63.7 57.9 56.2 58.3 25 58.8 57.0 71.1 64.7 63.0 65.3 30 65.6 63.7 78.9 72.0 70.3 72.8 35 72.8 71.0 87.3 79.9 78.1 80.8
40 80.5 78.7 96.2 88.2 86.4 89.3 45 88.7 87.0 105.6 97.1 95.2 98.4 50 97.4 95.8 115.7 106.5 104.7 108.1 55 106.6 105.1 126.4 116.5 114.7 118.5 60 116.4 115.1 137.7 127.2 125.3 129.4 65 126.7 125.6 149.7 138.4 136.6 141.1
70 137.6 136.8 162.4 150.3 148.6 153.4 75 149.1 148.7 175.8 162.9 161.2 166.4 80 161.2 161.2 189.9 176.1 174.6 180.2 85 174.0 174.4 204.8 190.1 188.8 194.8 90 187.4 188.4 220.4 204.8 203.7 210.1 95 201.4 203.1 236.9 220.3 219.4 226.3
100 216.2 218.7 254.3 236.6 235.9 243.4 105 231.7 235.4 272.5 253.7 253.4 261.3 110 247.9 252.1 291.6 271.6 271.7 280.2 115 264.9 270.2 311.7 290.5 290.9 300.0 120 282.7 289.1 332.7 310.2 311.1 320.8 125 301.4 308.9 354.8 330.9 332.3 342.6
130 320.8 329.7 377.9 352.6 354.5 365.5 135 341.2 351.5 402.2 375.3 377.8 389.4 140 362.6 374.3 427.5 399.0 402.2 414.5 145 385.0 398.1 454.1 423.8 427.7 440.7 150 408.4 423.0 482.0 449.8 454.4 468.1 TYPE SIZES NET LBS. TYPE COLOR CODE 

### Forane® 

### Cylinder Identification

R-11 CFC Orange R-12 CFC White R-502 CFC Lavender R-22 HCFC Green R-123 HCFC Light Blue Grey R-401A HCFC Pinkish Red R-401B HCFC Mustard R-402A HCFC Sand R-402B HCFC Olive R-408A HCFC Medium Purple R-409A HCFC Tan R-134a HFC Light Blue R-404A HFC Orange R-407C HFC Brown R-410A HFC Rose R-507 HFC Teal

COLOR CODE 

### Forane® 

### Cylinder Identification

R-11 100 (E), 200 (E), 650 (E) Orange R-12 30 (B), 50 (C), 145 (D) White R-502 30 (B), 50 (C), 125 (D) Lavender R-22 30 (B), 50 (C), 125 (D), 1000 (F), 1750 (G) Green R-123 100 (E), 200 (E) Light Blue Grey R-401A 30 (B), 125 (D) Pinkish Red R-401B 30 (B), 125 (D) Mustard R-402A 27 (B), 110 (D) Sand R-402B 13 (B) Olive R-408A 24 (B), 100 (D) Medium Purple R-409A 30 (B), 125 (D) Tan R-134a 30 (B), 125 (D), 1000 (F), 1750 (G) Light Blue R-404A 24 (B), 100 (D), 800 (F), 1300 (G) Orange R-407C 25 (B), 115 (D), 1600 (G) Brown R-410A 25 (B), 100 (D), 850 (F), 1350 (G) Rose R-507 25 (B), 100 (D), 800 (F), 1400 (G) Teal PRESSURE (PSIG)

13/24 25/27 30 lb. (B)

800 850 1000 lb.

(F)

1300/1350/1400/1600/1750 lb. (G) 50 lb. (C) 100 110 115/125 145 lb.

(D)

100 200 650 690 lb. Drum (E) Container Types Size not to scale

TGI 5M 4/06