Facility_Information

facility_id utility_codelegal_owner_nam legl_operator_name e legal_address_ty legal_address pe legal_city legal_state legal_zip

3131 17235 RRI EnergyRRI Energy Mid-Atlantic PH LLC operator Mid-Atlantic PH LLC 1000 Main Street Houston TX 77022

Page 1
Facility_Information

plant_namephysical_address phyical_cityphysical_statephysical_zipmailing_address mailing_citymailing_statemailing_zip

Shawville 250 Power Plant Drive Shawville PA 16873 250 Power Plant Drive, PO Box F Shawville PA 16873

Page 2
Facility_Information

RFA_small_entity ff_fired_coalff_fired_oil ff_fired_ngasff_fired_petcoke ff_fired_other ff_permitted_coal ff_permitted_oil ff_permitted_ngas

No TRUE TRUE FALSE FALSE TRUE TRUE TRUE FALSE

Page 3
Facility_Information

ff_permitted_petcoke ff_permitted_other deviation_reporting continuous_emissions cem_providedfacility_note

FALSE TRUE "Title V Operating Permit No. 17-00001, Condition B#023 Yes EPA Clean Air Markets, PADEP Zero was entered for the percentage on a mass or volume basis for o

Page 4
Facility_Information

age on a mass or volume basis for oil for all years per guidance, ICR FAQ #EICR-027.Actual date low sulfur fuel oil use began unkno

Page 5
Facility_Information

e low sulfur fuel oil use began unknown; date entered reflects 5 year title V recordkeeping requirement.Other Controls, ACI3 and ACI4

Page 6
Facility_Information

Other Controls, ACI3 and ACI4, were entered with a date of operation of 12/2009, which is incorrect. Neither control is currently opera

Page 7
Facility_Information

ect. Neither control is currently operating but the database limits the date to 12/2009. The anticipated dates of operation for controls ACI3 an

Page 8
Facility_Information

ates of operation for controls ACI3 and ACI4 are June 2010. These controls will be operated on a temporary basis at the operator's discretio

Page 9
Facility_Information

orary basis at the operator's discretion.Compliance with the filterable PM limit is determined by the average of 3 1-hour test runs; the a

Page 10
Facility_Information

e average of 3 1-hour test runs; the averaging period was chosen as 3 hours for that reason only.The averaging period for both Nox a

Page 11
Facility_Information

The averaging period for both Nox and SO2 limits are 30 day-rolling averages.All PM test report concentrations in gr/dscf except test 

Page 12
Facility_Information

concentrations in gr/dscf except test SH-186 PM Concentrations in lbs/dscfTest Sh-185AFlue Temp Run 2 301Flue Temp Run 

Page 13
Facility_Information

 Temp Run 2 301Flue Temp Run 3 301Test Sh-186ESP1A inFlue Temp Run 9 

Page 14
facility_contacts

facility_id contact_id contact_titlecontact_namecontact_phone1 contact_phone2 contact_email contact_primary

3131 1 Air Quality Specialist III Sharene Shealey 72459782327242553220sshealey@rrienergy TRUE.com

3131 2 Manager Keith A. Schm7245978193 idt kschmidt@rrienergy FALSE.com

Page 15
facility_coal_utilized

facility_id coal_type percentage_mass percentage_btu synfuel_typecoal_note

3131 bituminous 100 100

Page 16
facility_oil_utilized

facility_id oil_type percentage_volume percentage_btu other_type

3131 No.2 Fuel Oil (distillate) 100 100

Page 17
facility_other_materials

facility_id other_material permitted_burn actually_burnother_quantity other_quantity other_note _units rcra_utilize rcra_explain

3131 Non-HAP, non-VOC chemical cleaning waste liquids TRUE TRUE 20000 number/yearShawville unit 4 com No busted 60,000 gallons of non-HAP, nNo determination has been made r

Page 18
facility_other_materials

rcra_explain

No determination has been made regarding whether chemical cleaning waste would be burned in these units if the waste were subject to C

Page 19
facility_other_materials

e units if the waste were subject to CAA section 129. "No" was selected as the response because "Undetermined" is not an available choic

Page 20
facility_other_materials

determined" is not an available choice.

Page 21
boiler_information

facility_id boiler_id boiler_type boiler_otherbottom_design design_fuelheat_input max_heat_input MWe_capacity

3131 1 Wall firing - front firing Dry Bottomcoal 1345 1349 125

3131 2 Wall firing - front firing Dry Bottomcoal 1345 1349 125

3131 3 Tangential firing Dry Bottomcoal 1790 1794 188

3131 4 Tangential firing Dry Bottomcoal 1790 1794 188

Page 22
boiler_information

MWe_net_capacity design_gross_efficiency operating_gross_efficiency design_pressure operating_pressure design_tempoperating_temp design_reheat_multiple design_reheat_temp1

122 31.7 35.4 1800 1850 1050 1025 FALSE 1000

125 31.7 34.3 1800 1850 1050 1025 FALSE 1000

175 35.8 36 2400 2450 1050 1050 FALSE 1000

175 35.8 36.2 2400 2450 1050 1050 FALSE 1000

Page 23
boiler_information

design_reheat_temp2 operating_reheat_multiple operating_reheat_temp1 operating_reheat_temp2 hours_operatedvg_capacityapplicable_NSPS _factor retirement_yretirement_y ear ear_CBI

FALSE 960 6969.67 59.49 N FALSE

FALSE 960 6849.33 58.52 N FALSE

FALSE 1000 7283.67 60.53 N FALSE

FALSE 1000 7573 63.02 N FALSE

Page 24
boiler_information

NOx_controlSO2_controlcombustion_additives

Yes Yes Yes

Yes Yes Yes

Yes Yes No

Yes Yes No

Page 25
boiler_fuels

facility_id boiler_id fuel_type fuel_year percentage_massvol percentage_btu other_type

3131 1 coal - bituminous2007 100 99.67

3131 1 coal - bituminous2008 100 99.63

3131 1 coal - bituminous2009 100 99.07

3131 1 oil - distillate 2007 0 0.33

3131 1 oil - distillate 2008 0 0.37

3131 1 oil - distillate 2009 0 0.93

3131 2 coal - bituminous2007 100 99.61

3131 2 coal - bituminous2008 100 99.6

3131 2 coal - bituminous2009 100 98.99

3131 2 oil - distillate 2007 0 0.39

3131 2 oil - distillate 2008 0 0.4

3131 2 oil - distillate 2009 0 1.01

3131 3 coal - bituminous2007 100 99.65

3131 3 coal - bituminous2008 100 99.65

3131 3 coal - bituminous2009 100 99.51

3131 3 oil - distillate 2007 0 0.35

3131 3 oil - distillate 2008 0 0.35

3131 3 oil - distillate 2009 0 0.49

3131 4 coal - bituminous2007 100 99.79

3131 4 coal - bituminous2008 100 99.74

3131 4 coal - bituminous2009 100 99.34

3131 4 oil - distillate 2007 0 0.21

3131 4 oil - distillate 2008 0 0.26

3131 4 oil - distillate 2009 0 0.66

Page 26
boiler_control_NOx

facility_id boiler_id NOx_type NOx_other NOx_online

3131 1 Low NOx Burner 4/1/1999

3131 2 Low NOx Burner 4/1/1999

3131 3 Low NOx Burner 4/1/1999

3131 3 Overfire Air 4/1/1999

3131 4 Low NOx Burner 4/1/1999

3131 4 Overfire Air 4/1/1999

Page 27
boiler_control_SO2

facility_id boiler_id SO2_type SO2_other SO2_online

3131 1 Low Sulfur Fuel Oil 1/1/2005

3131 2 Low Sulfur Fuel Oil 1/1/2005

3131 3 Low Sulfur Fuel Oil 1/1/2005

3131 4 Low Sulfur Fuel Oil 1/1/2005

Page 28
boiler_additives

facility_id boiler_id boiler_additive additive_other additive_online

3131 1 Flue gas conditioning to control opacity 1/1/1995 (e.g., SO3 injection, ammonia, other)

3131 2 Flue gas conditioning to control opacity 3/1/1995 (e.g., SO3 injection, ammonia, other)

Page 29
facility_units

facility_id unit_id

3131 1

3131 2

3131 3

3131 4

Page 30
unit_boilers

facility_id unit_id boiler_id

3131 1 1

3131 2 2

3131 3 3

3131 4 4

Page 31
facility_controls

facility_id control_id control_groupcontrol_typecontrol_otherlegacy_control cntrol_onlinecontrol_offlineNOx_reagent

3131 ACI3 Other control Activated carbon injectionFALSE 12/1/2009

3131 ACI4 Other control Activated carbon injectionFALSE 12/1/2009

3131 ESP1A PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 6/1/1954

3131 ESP1B PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 6/1/1976

3131 ESP2A PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 6/1/1954

3131 ESP2B PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 6/1/1976

3131 ESP3A PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 6/1/1959

3131 ESP3B PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 3/1/1977

3131 ESP4A PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 6/1/1960

3131 ESP4B PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 3/1/1977

3131 SNCR1 NOx controlSelective Noncatalytic Reduction FALSE 5/1/2005 Urea

3131 SNCR2 NOx controlSelective Noncatalytic Reduction FALSE 5/1/2005 Urea

3131 SNCR3 NOx controlSelective Noncatalytic Reduction FALSE 5/1/2005 Urea

3131 SNCR4 NOx controlSelective Noncatalytic Reduction FALSE 5/1/2005 Urea

Page 32
facility_controls

reagent_other NOx_ammonia SO2_sorbent oher_sorbent SO2_scrubber_additive

Page 33
facility_sampling_ports

facility_id sampling_port_id

3131 1A

3131 1B

3131 1C

3131 1D

3131 2A

3131 2B

3131 2C

3131 2D

3131 34A

3131 34B

3131 34C

3131 34D

3131 AH 1 IN

3131 AH 2 IN

3131 AH 3 IN

3131 AH 4 IN

3131 ESP1A IN

3131 ESP1A OUT

3131 ESP1B IN

3131 ESP1B OUT

3131 ESP2A IN

3131 ESP2A OUT

3131 ESP2B IN

3131 ESP2B OUT

3131 ESP3A IN

3131 ESP3B IN

3131 ESP3B OUT

3131 ESP4A IN

3131 ESP4A OUT

3131 ESP4B IN

3131 ESP4B OUT

Page 34
facility_stacks

facility_id stack_id stack_heightstack_diameter sack_gas_velocity

3131 CS34 850 19 106.89

3131 S12 600 14.334 70.19

3131 S2

Page 35
configurations

facility_id configuration_id

3131 SHAW1-1

3131 SHAW1-2

3131 SHAW2-1

3131 SHAW2-2

3131 SHAW3-1

3131 SHAW3-2

3131 SHAW4-1

3131 SHAW4-2

Page 36
configuration_components

facility_id configuration_id component_idorder component_ty port_near pe

3131 SHAW1-1 1 1 Unit

3131 SHAW1-1 1A 8 Sampling Port pevious

3131 SHAW1-1 1B 8 Sampling Port pevious

3131 SHAW1-1 1C 8 Sampling Port pevious

3131 SHAW1-1 1D 8 Sampling Port pevious

3131 SHAW1-1 AH 1 IN 2 Sampling Port pevious

3131 SHAW1-1 ESP1A 4 PM control

3131 SHAW1-1 ESP1A IN 3 Sampling Port next

3131 SHAW1-1 ESP1A OUT 5 Sampling Port pevious

3131 SHAW1-1 ESP1B 6 PM control

3131 SHAW1-1 ESP1B OUT 7 Sampling Port pevious

3131 SHAW1-1 S12 8 Stack

3131 SHAW1-2 1 1 Unit

3131 SHAW1-2 1A 9 Sampling Port pevious

3131 SHAW1-2 1B 9 Sampling Port pevious

3131 SHAW1-2 1C 9 Sampling Port pevious

3131 SHAW1-2 1D 9 Sampling Port pevious

3131 SHAW1-2 AH 1 IN 2 Sampling Port pevious

3131 SHAW1-2 ESP1A 5 PM control

3131 SHAW1-2 ESP1A IN 4 Sampling Port next

3131 SHAW1-2 ESP1A OUT 6 Sampling Port pevious

3131 SHAW1-2 ESP1B 7 PM control

3131 SHAW1-2 ESP1B OUT 8 Sampling Port pevious

3131 SHAW1-2 S12 9 Stack

3131 SHAW1-2 SNCR1 3 NOx control

3131 SHAW2-1 2 1 Unit

3131 SHAW2-1 2A 8 Sampling Port pevious

3131 SHAW2-1 2B 8 Sampling Port pevious

3131 SHAW2-1 2C 8 Sampling Port pevious

3131 SHAW2-1 2D 8 Sampling Port pevious

3131 SHAW2-1 AH 2 IN 2 Sampling Port pevious

3131 SHAW2-1 ESP2A 4 PM control

3131 SHAW2-1 ESP2A IN 3 Sampling Port next

3131 SHAW2-1 ESP2A OUT 5 Sampling Port pevious

3131 SHAW2-1 ESP2B 6 PM control

3131 SHAW2-1 ESP2B OUT 7 Sampling Port pevious

3131 SHAW2-1 S12 8 Stack

3131 SHAW2-2 2 1 Unit

3131 SHAW2-2 2A 9 Sampling Port pevious

3131 SHAW2-2 2B 9 Sampling Port pevious

3131 SHAW2-2 2C 9 Sampling Port pevious

3131 SHAW2-2 2D 9 Sampling Port pevious

3131 SHAW2-2 AH 2 IN 2 Sampling Port pevious

3131 SHAW2-2 ESP2A 5 PM control

3131 SHAW2-2 ESP2A IN 4 Sampling Port next

3131 SHAW2-2 ESP2A OUT 6 Sampling Port pevious

3131 SHAW2-2 ESP2B 7 PM control

3131 SHAW2-2 ESP2B OUT 8 Sampling Port pevious

3131 SHAW2-2 S12 9 Stack

3131 SHAW2-2 SNCR2 3 NOx control

3131 SHAW3-1 3 1 Unit

Page 37
configuration_components

3131 SHAW3-1 34A 4 Sampling Port pevious

3131 SHAW3-1 34B 4 Sampling Port pevious

3131 SHAW3-1 34C 4 Sampling Port pevious

3131 SHAW3-1 34D 4 Sampling Port pevious

3131 SHAW3-1 CS34 4 Stack

3131 SHAW3-1 ESP3A 2 PM control

3131 SHAW3-1 ESP3B 3 PM control

3131 SHAW3-2 3 1 Unit

3131 SHAW3-2 34A 5 Sampling Port pevious

3131 SHAW3-2 34B 5 Sampling Port pevious

3131 SHAW3-2 34C 5 Sampling Port pevious

3131 SHAW3-2 34D 5 Sampling Port pevious

3131 SHAW3-2 CS34 5 Stack

3131 SHAW3-2 ESP3A 3 PM control

3131 SHAW3-2 ESP3B 4 PM control

3131 SHAW3-2 SNCR3 2 NOx control

3131 SHAW4-1 34A 8 Sampling Port pevious

3131 SHAW4-1 34B 8 Sampling Port pevious

3131 SHAW4-1 34C 8 Sampling Port pevious

3131 SHAW4-1 34D 8 Sampling Port pevious

3131 SHAW4-1 4 1 Unit

3131 SHAW4-1 AH 4 IN 2 Sampling Port pevious

3131 SHAW4-1 CS34 8 Stack

3131 SHAW4-1 ESP4A 4 PM control

3131 SHAW4-1 ESP4A IN 3 Sampling Port next

3131 SHAW4-1 ESP4A OUT 5 Sampling Port pevious

3131 SHAW4-1 ESP4B 6 PM control

3131 SHAW4-1 ESP4B OUT 7 Sampling Port pevious

3131 SHAW4-2 34A 9 Sampling Port pevious

3131 SHAW4-2 34B 9 Sampling Port pevious

3131 SHAW4-2 34C 9 Sampling Port pevious

3131 SHAW4-2 34D 9 Sampling Port pevious

3131 SHAW4-2 4 1 Unit

3131 SHAW4-2 AH 4 IN 2 Sampling Port pevious

3131 SHAW4-2 CS34 9 Stack

3131 SHAW4-2 ESP4A 5 PM control

3131 SHAW4-2 ESP4A IN 4 Sampling Port next

3131 SHAW4-2 ESP4A OUT 6 Sampling Port pevious

3131 SHAW4-2 ESP4B 7 PM control

3131 SHAW4-2 ESP4B OUT 8 Sampling Port pevious

3131 SHAW4-2 SNCR4 3 NOx control

Page 38
configuration_pollutants1

facility_id configuration_id pollutant_nampermit_ty e pe_1emlimit_1 emlimit_units_1 avg_period_1emlimit_2 emlimit_units_2

3131 SHAW4-2 PM (Filterable) Fderal - Title V Operating Permit 0.1 pound per million British Thermal Unit (lb/MMBtu) 3 hours

3131 SHAW4-2 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.45 pound per million British Thermal Unit (lb/MMBtu) 30 days 0.45 pound per million British Thermal U

3131 SHAW4-2 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 3.7 pound per million British Thermal Unit (lb/MMBtu) 30 days 4.8 pound per million British Thermal U

3131 SHAW1-1 PM (Filterable) Fderal - Title V Operating Permit 0.1 pound per million British Thermal Unit (lb/MMBtu) 3 hours

3131 SHAW1-1 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.524 pound per million British Thermal Unit (lb/MMBtu) 30 days 0.524 pound per million British Thermal U

3131 SHAW1-1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 3.7 pound per million British Thermal Unit (lb/MMBtu) 30 days 4.8 pound per million British Thermal U

3131 SHAW1-2 PM (Filterable) Fderal - Title V Operating Permit 0.1 pound per million British Thermal Unit (lb/MMBtu) 3 hours

3131 SHAW1-2 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.524 pound per million British Thermal Unit (lb/MMBtu) 30 days 0.524 pound per million British Thermal U

3131 SHAW1-2 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 3.7 pound per million British Thermal Unit (lb/MMBtu) 30 days 4.8 pound per million British Thermal U

3131 SHAW2-1 PM (Filterable) Fderal - Title V Operating Permit 0.1 pound per million British Thermal Unit (lb/MMBtu) 3 hours

3131 SHAW2-2 PM (Filterable) Fderal - Title V Operating Permit 0.1 pound per million British Thermal Unit (lb/MMBtu) 3 hours

3131 SHAW3-1 PM (Filterable) Fderal - Title V Operating Permit 0.1 pound per million British Thermal Unit (lb/MMBtu) 3 hours

3131 SHAW3-2 PM (Filterable) Fderal - Title V Operating Permit 0.1 pound per million British Thermal Unit (lb/MMBtu) 3 hours

3131 SHAW4-1 PM (Filterable) Fderal - Title V Operating Permit 0.1 pound per million British Thermal Unit (lb/MMBtu) 3 hours

3131 SHAW2-1 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.542 pound per million British Thermal Unit (lb/MMBtu) 30 days 0.542 pound per million British Thermal U

3131 SHAW2-1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 3.7 pound per million British Thermal Unit (lb/MMBtu) 30 days 4.8 pound per million British Thermal U

3131 SHAW2-2 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.542 pound per million British Thermal Unit (lb/MMBtu) 30 days 0.542 pound per million British Thermal U

3131 SHAW2-2 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 3.7 pound per million British Thermal Unit (lb/MMBtu) 30 days 4.8 pound per million British Thermal U

3131 SHAW3-1 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.45 pound per million British Thermal Unit (lb/MMBtu) 30 days 0.45 pound per million British Thermal U

3131 SHAW3-1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 3.7 pound per million British Thermal Unit (lb/MMBtu) 30 days 4.8 pound per million British Thermal U

3131 SHAW3-2 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.45 pound per million British Thermal Unit (lb/MMBtu) 30 days 0.45 pound per million British Thermal U

3131 SHAW3-2 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 3.7 pound per million British Thermal Unit (lb/MMBtu) 30 days 4.8 pound per million British Thermal U

3131 SHAW4-1 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.45 pound per million British Thermal Unit (lb/MMBtu) 30 days 0.45 pound per million British Thermal U

3131 SHAW4-1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 3.7 pound per million British Thermal Unit (lb/MMBtu) 30 days 4.8 pound per million British Thermal U

Page 39
configuration_pollutants1

avg_period_2emlimit_3 emlimit_units_3 avg_period_3emlimit_4 emlimit_units_4 avg_period_4emlimit_details test_method

Compliance with the filterable PM limit is deterEPA RM5 

annual The annual limit is per the phase II acid rain pe

daily 4 pound per million British Thermal Unit (lb/MMBtu) daily 4 lb/mmBtu not to be exceeded more than 2 d

Compliance with the filterable PM limit is deterEPA RM5 

annual The annual limit is per the phase II acid rain pe

daily 4 pound per million British Thermal Unit (lb/MMBtu) daily 4.0 lb/mmBtu daily, not to be exceeded more t

Compliance with the filterable PM limit is deterEPA RM5 

annual The annual limit is per the phase II acid rain pe

daily 4 pound per million British Thermal Unit (lb/MMBtu) daily 4.0 lb/mmBtu daily, not to be exceeded more t

Compliance with the filterable PM limit is deterEPA RM5 

Compliance with the filterable PM limit is deterEPA RM5 

Compliance with the filterable PM limit is deterEPA RM5 

Compliance with the filterable PM limit is deterEPA RM5 

Compliance with the filterable PM limit is deterEPA RM5 

annual The annual limit is per the phase II acid rain pe

daily 4 pound per million British Thermal Unit (lb/MMBtu) daily 4.0 lb/mmBtu daily, not to be exceeded more t

annual The annual limit is per the phase II acid rain pe

daily 4 pound per million British Thermal Unit (lb/MMBtu) daily 4.0 lb/mmBtu daily, not to be exceeded more t

annual The annual limit is per the phase II acid rain pe

daily 4 pound per million British Thermal Unit (lb/MMBtu) daily 4.0 lb/mmBtu daily, not to be exceeded more t

annual The annual limit is per the phase II acid rain pe

daily 4 pound per million British Thermal Unit (lb/MMBtu) daily 4.0 lb/mmBtu daily, not to be exceeded more t

annual The annual limit is per the phase II acid rain pe

daily 4 pound per million British Thermal Unit (lb/MMBtu) daily 4.0 lb/mmBtu daily, not to be exceeded more t

Page 40
configuration_pollutants1

emrate emrate_unitsguarantee_level_explainreq_monitoringeq_recordkeeping req_reporting

Performance of compliance test Heat Input per per 40 CFR 75 and PA DEP Continuous Source MonitSubmittal of stack test report

al limit is per the phase II acid rain permit. Operation and maintenance of certfied NOx and diluent CEMs per 40 CFR 75 rePer 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

tu not to be exceeded more than 2 days in any running 30-day Operation and maintenance of certfied SO2 and diluent CEMs per 40 CFR 75 re period Per 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

Performance of compliance test Heat Input per per 40 CFR 75 and PA DEP Continuous Source MonitSubmittal of stack test report

al limit is per the phase II acid rain permit Operation and maintenance of certfied NOx and diluent CEMs per 40 CFR 75 rePer 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

Btu daily, not to be exceeded more than 2 days in any running 30-day Operation and maintenance of certfied SO2 and diluent CEMs per 40 CFR 75 re period Per 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

Performance of compliance test Heat Input per per 40 CFR 75 and PA DEP Continuous Source MonitSubmittal of stack test report

al limit is per the phase II acid rain permit. Operation and maintenance of certfied Nox and diluent CEMs per 40 CFR 75 reqPer 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

Btu daily, not to be exceeded more than 2 days in any running 30-day Operation and maintenance of certfied SO2 and diluent CEMs per 40 CFR 75 re period Per 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

Performance of compliance test Heat Input per per 40 CFR 75 and PA DEP Continuous Source MonitSubmittal of stack test report

Performance of compliance test Heat Input per per 40 CFR 75 and PA DEP Continuous Source MonitSubmittal of stack test report

Performance of compliance test Heat Input per per 40 CFR 75 and PA DEP Continuous Source MonitSubmittal of stack test report

Performance of compliance test Heat Input per per 40 CFR 75 and PA DEP Continuous Source MonitSubmittal of stack test report

Performance of compliance test Heat Input per per 40 CFR 75 and PA DEP Continuous Source MonitSubmittal of stack test report

al limit is per the phase II acid rain permit. Operation and maintenance of certfied NOx and diluent CEMs per 40 CFR 75 rePer 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

Btu daily, not to be exceeded more than 2 days in any running 30-day Operation and maintenance of certfied SO2 and diluent CEMs per 40 CFR 75 re period. Per 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

al limit is per the phase II acid rain permit. Operation and maintenance of certfied NOx and diluent CEMs per 40 CFR 75 rePer 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

Btu daily, not to be exceeded more than 2 days in any running 30-day Operation and maintenance of certfied SO2 and diluent CEMs per 40 CFR 75 re period. Per 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

al limit is per the phase II acid rain permit. Operation and maintenance of certfied NOx and diluent CEMs per 40 CFR 75 rePer 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

Btu daily, not to be exceeded more than 2 days in any running 30-day Operation and maintenance of certfied SO2 and diluent CEMs per 40 CFR 75 re period. Per 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

al limit is per the phase II acid rain permit. Operation and maintenance of certfied NOx and diluent CEMs per 40 CFR 75 rePer 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

Btu daily, not to be exceeded more than 2 days in any running 30-day Operation and maintenance of certfied SO2 and diluent CEMs per 40 CFR 75 re period Per 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

al limit is per the phase II acid rain permit. Operation and maintenance of certfied NOx and diluent CEMs per 40 CFR 75 rePer 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

Btu daily, not to be exceeded more than 2 days in any running 30-day Operation and maintenance of certfied SO2 and diluent CEMs per 40 CFR 75 re period. Per 40 CFR 75 and PA DEP Continuous Source Monitoring Manual rQuarterly EDRs to EPA; Quarterly CEMs reports to PA DE

Page 41
configuration_pollutants1

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

PA; Quarterly CEMs reports to PA DEP

Page 42
control_technologies

facility_id configuration_id component_idcontrol_id project_titleproject_typevendor_namevndor_contact vendor_phone

Page 43
control_technologies

vendor_address vndor_cityvendor_statevendor_zip actual_start_date projected_start_date end_date sorbent chemical_additive

Page 44
control_technologies

injection_point HAP_emission_reduction HAP_emission_rate HAP_emission_rate_units HAP_achieved_reduction HAP_achieved_rate HAP_achieved_rate_units feed_rate feed_rate_units

Page 45
control_technologies

feed_rate_units

Page 46
control_coal_ranks

facility_id configuration_id component_idcontrol_id coal_type

Page 47
control_pollutants1

facility_id configuration_id component_idcontrol_id pollutant_name

Page 48
control_costs

facility_id configuration_id component_idcontrol_id boiler_retrofit boiler_new_install total_capital_investm total_operating_costs entbase_year

Page 49
control_costs

CBI

Page 50
misc_controls

facility_id misc_control_id control_description

Page 51
misc_control_configurations

facility_id misc_control_id configuration_id

Page 52
fuel_shipments

facility_id shipment_idshipment_date amount_received amount_unitsfuel_type state_countryother_countrycounty

3131 coal1 1/1/2009 126809 short tons (2000 lbs) coal PA PA - Clearfield

3131 coal10 10/1/2009 39469 short tons (2000 lbs) coal PA PA - Clearfield

3131 coal11 11/1/2009 90074 short tons (2000 lbs) coal PA PA - Clearfield

3131 coal12 12/1/2009 99626 short tons (2000 lbs) coal PA PA - Clearfield

3131 coal2 2/1/2009 133997 short tons (2000 lbs) coal PA PA - Clearfield

3131 coal3 3/1/2009 88793 short tons (2000 lbs) coal PA PA - Clearfield

3131 coal4 4/1/2009 51611 short tons (2000 lbs) coal PA PA - Clearfield

3131 coal5 5/1/2009 47271 short tons (2000 lbs) coal PA PA - Clearfield

3131 coal6 6/1/2009 50807 short tons (2000 lbs) coal PA PA - Clearfield

3131 coal7 7/1/2009 58116 short tons (2000 lbs) coal PA PA - Clearfield

3131 coal8 8/1/2009 85697 short tons (2000 lbs) coal PA PA - Clearfield

3131 coal9 9/1/2009 90067 short tons (2000 lbs) coal PA PA - Clearfield

3131 oil1 1/1/2009 1735 barrels oil PA PA - Warren

3131 oil10 10/1/2009 1803 barrels oil PA PA - Warren

3131 oil11 11/1/2009 1802 barrels oil PA PA - Warren

3131 oil12 12/1/2009 2181 barrels oil PA PA - Warren

3131 oil2 2/1/2009 1812 barrels oil PA PA - Warren

3131 oil3 3/1/2009 899 barrels oil PA PA - Warren

3131 oil4 4/1/2009 3626 barrels oil PA PA - Warren

3131 oil5 5/1/2009 1815 barrels oil PA PA - Warren

3131 oil6 6/1/2009 3566 barrels oil PA PA - Warren

3131 oil7 7/1/2009 3586 barrels oil PA PA - Warren

3131 oil8 8/1/2009 1776 barrels oil PA PA - Warren

3131 oil9 9/1/2009 1772 barrels oil PA PA - Warren

Page 53
fuel_shipments

coal_seam shipment_method

PA - Clearfield Trucks

PA - Clearfield Trucks

PA - Clearfield Trucks

PA - Clearfield Trucks

PA - Clearfield Trucks

PA - Clearfield Trucks

PA - Clearfield Trucks

PA - Clearfield Trucks

PA - Clearfield Trucks

PA - Clearfield Trucks

PA - Clearfield Trucks

PA - Clearfield Trucks

PA - Warren Trucks

PA - Warren Trucks

PA - Warren Trucks

PA - Warren Trucks

PA - Warren Trucks

PA - Warren Trucks

PA - Warren Trucks

PA - Warren Trucks

PA - Warren Trucks

PA - Warren Trucks

PA - Warren Trucks

PA - Warren Trucks

Page 54
fuel_shipment_configurations

facility_id shipment_idconfiguration_id

3131 coal1 SHAW1-1

3131 coal1 SHAW2-1

3131 coal1 SHAW3-1

3131 coal1 SHAW4-1

3131 coal10 SHAW1-1

3131 coal10 SHAW2-1

3131 coal10 SHAW3-1

3131 coal10 SHAW4-1

3131 coal11 SHAW1-1

3131 coal11 SHAW2-1

3131 coal11 SHAW3-1

3131 coal11 SHAW4-1

3131 coal12 SHAW1-1

3131 coal12 SHAW2-1

3131 coal12 SHAW3-1

3131 coal12 SHAW4-1

3131 coal2 SHAW1-1

3131 coal2 SHAW2-1

3131 coal2 SHAW3-1

3131 coal2 SHAW4-1

3131 coal3 SHAW1-1

3131 coal3 SHAW2-1

3131 coal3 SHAW3-1

3131 coal3 SHAW4-1

3131 coal4 SHAW1-1

3131 coal4 SHAW2-1

3131 coal4 SHAW3-1

3131 coal4 SHAW4-1

3131 coal5 SHAW1-1

3131 coal5 SHAW1-2

3131 coal5 SHAW2-1

3131 coal5 SHAW2-2

3131 coal5 SHAW3-1

3131 coal5 SHAW3-2

3131 coal5 SHAW4-1

3131 coal5 SHAW4-2

3131 coal6 SHAW1-1

3131 coal6 SHAW1-2

3131 coal6 SHAW2-1

3131 coal6 SHAW2-2

3131 coal6 SHAW3-1

3131 coal6 SHAW3-2

3131 coal6 SHAW4-1

3131 coal6 SHAW4-2

3131 coal7 SHAW1-1

3131 coal7 SHAW1-2

3131 coal7 SHAW2-1

3131 coal7 SHAW2-2

3131 coal7 SHAW3-1

3131 coal7 SHAW3-2

3131 coal7 SHAW4-1

Page 55
fuel_shipment_configurations

3131 coal7 SHAW4-2

3131 coal8 SHAW1-1

3131 coal8 SHAW1-2

3131 coal8 SHAW2-1

3131 coal8 SHAW2-2

3131 coal8 SHAW3-1

3131 coal8 SHAW3-2

3131 coal8 SHAW4-1

3131 coal8 SHAW4-2

3131 coal9 SHAW1-1

3131 coal9 SHAW1-2

3131 coal9 SHAW2-1

3131 coal9 SHAW2-2

3131 coal9 SHAW3-1

3131 coal9 SHAW3-2

3131 coal9 SHAW4-1

3131 coal9 SHAW4-2

3131 oil1 SHAW1-1

3131 oil1 SHAW2-1

3131 oil1 SHAW3-1

3131 oil1 SHAW4-1

3131 oil10 SHAW1-1

3131 oil10 SHAW2-1

3131 oil10 SHAW3-1

3131 oil10 SHAW4-1

3131 oil11 SHAW1-1

3131 oil11 SHAW2-1

3131 oil11 SHAW3-1

3131 oil11 SHAW4-1

3131 oil12 SHAW1-1

3131 oil12 SHAW2-1

3131 oil12 SHAW3-1

3131 oil12 SHAW4-1

3131 oil2 SHAW1-1

3131 oil2 SHAW2-1

3131 oil2 SHAW3-1

3131 oil2 SHAW4-1

3131 oil3 SHAW1-1

3131 oil3 SHAW2-1

3131 oil3 SHAW3-1

3131 oil3 SHAW4-1

3131 oil4 SHAW1-1

3131 oil4 SHAW2-1

3131 oil4 SHAW3-1

3131 oil4 SHAW4-1

3131 oil5 SHAW1-1

3131 oil5 SHAW1-2

3131 oil5 SHAW2-1

3131 oil5 SHAW2-2

3131 oil5 SHAW3-1

3131 oil5 SHAW3-2

3131 oil5 SHAW4-1

Page 56
fuel_shipment_configurations

3131 oil5 SHAW4-2

3131 oil6 SHAW1-1

3131 oil6 SHAW1-2

3131 oil6 SHAW2-1

3131 oil6 SHAW2-2

3131 oil6 SHAW3-1

3131 oil6 SHAW3-2

3131 oil6 SHAW4-1

3131 oil6 SHAW4-2

3131 oil7 SHAW1-1

3131 oil7 SHAW1-2

3131 oil7 SHAW2-1

3131 oil7 SHAW2-2

3131 oil7 SHAW3-1

3131 oil7 SHAW3-2

3131 oil7 SHAW4-1

3131 oil7 SHAW4-2

3131 oil8 SHAW1-1

3131 oil8 SHAW1-2

3131 oil8 SHAW2-1

3131 oil8 SHAW2-2

3131 oil8 SHAW3-1

3131 oil8 SHAW3-2

3131 oil8 SHAW4-1

3131 oil8 SHAW4-2

3131 oil9 SHAW1-1

3131 oil9 SHAW1-2

3131 oil9 SHAW2-1

3131 oil9 SHAW2-2

3131 oil9 SHAW3-1

3131 oil9 SHAW3-2

3131 oil9 SHAW4-1

3131 oil9 SHAW4-2

Page 57
fuel_shipment_samples

facility_id shipment_idsample_id amount_fuelamount_fuel_units total_sulfur ash_contentheating_valuehating_units

Page 58
fuel_shipment_samples

chlorine chlorine_unitsfluorine fluorine_unitsdata_provideddata_other_specified supplier_typesupplier_name supplier_address

Page 59
fuel_shipment_samples

supplier_citysupplier_statesupplier_ziplab_name lab_addresslab_city lab_state lab_zip analysis_copies

Page 60
fuel_shipment_samples

analysis_copies

Page 61
fuel_sample_pollutants

facility_id shipment_idsample_id fuel_pollutant pollutant_conc pollutant_conc_units pollutant_conc_ND pollutant_conc_MDL

Page 62
test_reports

facility_id report_id report_typeother_type report_description report_begin_date report_end_date before_control during_deviation

3131 SH-181 other Diagnostic Hg LMEU test ######## ######## No No

3131 SH-181A other Diagnostic Hg LMEU ######## ######## No No

3131 SH-181B other Diagnostic Hg LMEU Test ######## ######## No No

3131 SH-184 U3-4other Informational Request Test for PM Filterable and Condensable, and Lead Emissions. EPA Methods: EP2/26/2009 2/26/2009 No No

3131 SH-184-U1other Informational Request Test for PM Filterable and Condensable, and Lead Emissions. EPA Methods: EP4/8/2009 4/8/2009 No No

3131 SH-184-U2other Informational Request Test for PM Filterable and Condensable, and Lead Emissions. EPA Methods: EP4/9/2009 4/9/2009 No No

3131 Sh-185A other Diagnostic Test for PM Filterable and Condensable Pre Hg Emission Control equiptment. E6/11/2009 6/11/2009 No No

3131 SH-185B other Diagnostic Test for PM Filterable and Condensable Pre Hg Emission Control equiptment. E7/24/2009 7/24/2009 No No

3131 SH-186 other Diagnostic Test for PM Filterable and Condensable Pre Hg Emission Control equiptment. E7/8/2009 7/10/2009 Yes No

3131 Unit 1 Baseline HG other Diagnostic Baseline Hg######## ######## No No

3131 Unit 1 Boiler performance other diagnostic diagnostic test for the gas characterization of Hg strategy ######## ######## Yes No

3131 Unit 2 Baseline Hg other Diagnostic Baseline Hg######## ######## No No

3131 Unit 2 Boiler Performance other Diagnostic diagnostic test for the gas characterization of Hg strategy ######## ######## Yes No

3131 Unit 3-4 Baseline Hg other Diagnostic Baseline Hg######## ######## No No

Page 63
test_reports

deviation_reports

No

No

No

No

No

No

No

No

No

No

No

No

No

No

Page 64
test_report_configurations

facility_id report_id configuration_id

3131 SH-181 SHAW1-1

3131 SH-181A SHAW2-1

3131 SH-181B SHAW3-1

3131 SH-181B SHAW4-1

3131 SH-184 U3-4SHAW3-2

3131 SH-184 U3-4SHAW4-2

3131 SH-184-U1SHAW1-2

3131 SH-184-U2SHAW2-2

3131 Sh-185A SHAW1-2

3131 SH-185B SHAW1-2

3131 SH-186 SHAW1-2

3131 Unit 1 Baseline HG SHAW1-2

3131 Unit 1 Boiler performance SHAW1-1

3131 Unit 2 Baseline Hg SHAW2-2

3131 Unit 2 Boiler Performance SHAW2-1

3131 Unit 3-4 Baseline Hg SHAW3-2

3131 Unit 3-4 Baseline Hg SHAW4-2

Page 65
test_report_fuels

facility_id report_id fuel_id

3131 SH-181 Coal

3131 SH-181A Coal

3131 SH-181B Coal

3131 SH-184 U3-4Coal

3131 SH-184-U1Coal

3131 SH-184-U2Coal

3131 Sh-185A Coal

3131 SH-185B Coal

3131 SH-186 Coal

3131 Unit 1 Baseline HG Coal

3131 Unit 1 Boiler performance Coal

3131 Unit 2 Baseline Hg Coal

3131 Unit 2 Boiler Performance Coal

3131 Unit 3-4 Baseline Hg Coal

Page 66
test_report_fuel_types

facility_id report_id fuel_id fuel_type percentage_massvol percentage_btu other_type

3131 SH-181 Coal coal - bituminous 100 100

3131 SH-181A Coal coal - bituminous 100 100

3131 SH-181B Coal coal - bituminous 100 100

3131 SH-184 U3-4Coal coal - bituminous 100 100

3131 SH-184-U1Coal coal - bituminous 100 100

3131 SH-184-U2Coal coal - bituminous 100 100

3131 Sh-185A Coal coal - bituminous 100 100

3131 SH-185B Coal coal - bituminous 100 100

3131 SH-186 Coal coal - bituminous 100 100

3131 Unit 1 Baseline HG Coal coal - bituminous 100 100

3131 Unit 1 Boiler performance Coal coal - bituminous 100 100

3131 Unit 2 Baseline Hg Coal coal - bituminous 100 100

3131 Unit 2 Boiler Performance Coal coal - bituminous 100 100

3131 Unit 3-4 Baseline Hg Coal coal - bituminous 100 100

Page 67
cem_data

facility_id time_periodcem_period_description

3131 01/01/2005 - present SO2 and NOx CEMS data and opacity COMS data available from 01/01/2005 to present.

3131 12/21/2007 - 11/10/2009 Hg CEMS were installed and data were collected during the time period specified. The data were never 

3131 12/21/2007 - present Hg CEMS were installed and data were collected during the time period specified. The data were never 

Page 68
cem_data

1/01/2005 to present.

eriod specified. The data were never properly quality assured or reported in accordance with CAMR or State regulations. Data are not being s

eriod specified. The data were never properly quality assured or reported in accordance with CAMR or State regulations. Data are not being s

Page 69
cem_data

tate regulations. Data are not being submitted due to the lack of proper QA/QC. Units1&2

tate regulations. Data are not being submitted due to the lack of proper QA/QC.Units3&4

Page 70
cem_data_pollutants1

facility_id time_periodpollutant_name

3131 01/01/2005 - present Sulfur Dioxide (SO2)

3131 01/01/2005 - present Nitrogen Oxide (NOx)

3131 12/21/2007 - 11/10/2009 Oxidized Mercury (Hg++)

3131 12/21/2007 - 11/10/2009 Elemental Mercury (Hg0)

3131 12/21/2007 - 11/10/2009 Total Mercury (Hgt)

3131 12/21/2007 - present Oxidized Mercury (Hg++)

3131 12/21/2007 - present Elemental Mercury (Hg0)

3131 12/21/2007 - present Total Mercury (Hgt)

Page 71
test_report_sampling

facility_id report_id sampling_port_id point_differpoint_description befre_SO2_device point_orientation normal_bypass_percent testing_bypass_percent

3131 SH-181 S12 No No

3131 SH-181A S12 No No

3131 SH-181B CS34 No No

3131 SH-184 U3-4CS34 No No

3131 SH-184-U1S12 No No

3131 SH-184-U2S12 No No

3131 Sh-185A S12 No No

3131 SH-185B S12 No No

3131 SH-186 ESP1A IN No Inlet to ESP A side No

3131 SH-186 ESP1A OUTNo Sampling at the Inlet to ESP B No

3131 SH-186 S12 No No

3131 Unit 1 Baseline HG S12 No No

3131 Unit 1 Boiler performance AH 1 IN No No

3131 Unit 1 Boiler performance ESP1B OUTNo testing at outlet of ESP No

3131 Unit 2 Baseline Hg S12 No No

3131 Unit 2 Boiler Performance AH 2 IN No No

3131 Unit 2 Boiler Performance ESP2B OUTNo No

3131 Unit 3-4 Baseline Hg CS34 No No

Page 72
test_report_sampling

fg_fraction

Page 73
sampling_runs

facility_id report_id sampling_port_id run_id start_datetime end_datetimunit_load e net_generation fg_moisture_content

3131 SH-181 S12 1 ######## ######## 120.5 5.84

3131 SH-181 S12 2 ######## ######## 122 5.82

3131 SH-181 S12 3 ######## ######## 121.9 5.87

3131 SH-181 S12 4 ######## ######## 121.9 5.83

3131 SH-181A S12 1 ######## ######## 79.9 6.06

3131 SH-181A S12 2 ######## ######## 80 6.07

3131 SH-181A S12 3 ######## ######## 76 6.25

3131 SH-181A S12 4 ######## ######## 80 5.88

3131 SH-181B CS34 1 ######## ######## 274 6.1

3131 SH-181B CS34 2 ######## ######## 291.4 6.09

3131 SH-181B CS34 3 ######## ######## 279.4 6.18

3131 SH-181B CS34 4 ######## ######## 282.3 6.27

3131 SH-184 U3-4CS34 1 2/26/2009 2/26/2009 334.5 5.9

3131 SH-184 U3-4CS34 2 2/26/2009 2/26/2009 335.4 5.6

3131 SH-184 U3-4CS34 3 2/26/2009 2/26/2009 335.2 5.5

3131 SH-184-U1S12 1 4/8/2009 4/8/2009 127.9 6

3131 SH-184-U1S12 2 4/8/2009 4/8/2009 128 5.5

3131 SH-184-U1S12 3 4/8/2009 4/8/2009 127.9 5

3131 SH-184-U2S12 1 4/9/2009 4/9/2009 124.4 6.1

3131 SH-184-U2S12 2 4/9/2009 4/9/2009 125.7 5.7

3131 SH-184-U2S12 3 4/9/2009 4/9/2009 125.8 5.7

3131 Sh-185A S12 1 6/11/2009 6/11/2009 123 5.89

3131 Sh-185A S12 2 6/11/2009 6/11/2009 122.8 6.78

3131 Sh-185A S12 3 6/11/2009 6/11/2009 122.9 6.26

3131 SH-185B S12 1 7/24/2009 7/24/2009 125.9 6.14

3131 SH-185B S12 2 7/24/2009 7/24/2009 126 5.97

3131 SH-185B S12 3 7/24/2009 7/24/2009 126 6.49

3131 SH-186 ESP1A IN 1 7/8/2009 7/8/2009 105 6.58

3131 SH-186 ESP1A IN 2 7/8/2009 7/8/2009 105 6.17

3131 SH-186 ESP1A IN 3 7/8/2009 7/8/2009 105 5.63

3131 SH-186 ESP1A IN 4 7/10/2009 7/10/2009 105 6.68

3131 SH-186 ESP1A IN 5 7/10/2009 7/10/2009 105 6.93

3131 SH-186 ESP1A IN 6 7/9/2009 7/9/2009 118 6.03

3131 SH-186 ESP1A IN 7 7/9/2009 7/9/2009 110 6.83

3131 SH-186 ESP1A IN 8 7/9/2009 7/9/2009 110 6.54

3131 SH-186 ESP1A IN 9 7/9/2009 7/9/2009 110 6.65

3131 SH-186 ESP1A OUT1 7/8/2009 7/8/2009 105 5.4

3131 SH-186 ESP1A OUT2 7/8/2009 7/8/2009 105 5.16

3131 SH-186 ESP1A OUT3 7/8/2009 7/8/2009 105 5.73

3131 SH-186 ESP1A OUT4 7/10/2009 7/10/2009 105 5.57

3131 SH-186 ESP1A OUT5 7/10/2009 7/10/2009 105 5.94

3131 SH-186 ESP1A OUT6 7/9/2009 7/9/2009 118 5.43

3131 SH-186 ESP1A OUT7 7/9/2009 7/9/2009 110 6.31

3131 SH-186 ESP1A OUT8 7/9/2009 7/9/2009 110 5.54

3131 SH-186 ESP1A OUT9 7/9/2009 7/9/2009 110 5.39

3131 SH-186 S12 1 7/8/2009 7/8/2009 105 6.41

3131 SH-186 S12 2 7/8/2009 7/8/2009 105 6.59

3131 SH-186 S12 3 7/8/2009 7/8/2009 105 6.52

3131 SH-186 S12 4 7/9/2009 7/9/2009 118 6.65

3131 Unit 1 Baseline HG S12 1 ######## ########

3131 Unit 1 Boiler performance AH 1 IN 1 ######## ########

Page 74
sampling_runs

3131 Unit 1 Boiler performance AH 1 IN 2 ######## ########

3131 Unit 1 Boiler performance AH 1 IN 3 ######## ########

3131 Unit 1 Boiler performance AH 1 IN 4 ######## ########

3131 Unit 1 Boiler performance ESP1B OUT1 ######## ########

3131 Unit 1 Boiler performance ESP1B OUT2 ######## ########

3131 Unit 1 Boiler performance ESP1B OUT3 ######## ########

3131 Unit 2 Baseline Hg S12 1 ######## ########

3131 Unit 2 Boiler Performance AH 2 IN 1 ######## ########

3131 Unit 2 Boiler Performance AH 2 IN 2 ######## ########

3131 Unit 2 Boiler Performance AH 2 IN 3 ######## ########

3131 Unit 2 Boiler Performance ESP2B OUT1 ######## ########

3131 Unit 2 Boiler Performance ESP2B OUT2 ######## ########

3131 Unit 2 Boiler Performance ESP2B OUT3 ######## ########

3131 Unit 3-4 Baseline Hg CS34 1 ######## ########

Page 75
sampling_runs

fg_flow_ratefg_flow_rate_units standard_temperature standard_pressure normal_temperature normal_pressure fg_oxygen_content fg_CO2_content fg_temperature

0.9705 252

0.977 253

0.977 254

0.977 255.5

0.9625 244

0.9625 247.2

0.9625 246.5

0.9624 246.5

0.958 243.5

0.961 244.5

0.961 244.5

0.961 244.5

931918 dscfm 0.966 8.9 11.3 253

927004 dscfm 0.965 8.7 11 258

919965 dscfm 0.965 5.5 11 262

334247 dscfm 0.961 9.1 10.6 281

323866 dscfm 0.961 9.1 10.6 282

350094 dscfm 0.962 9.1 10.4 290

374033 dscfm 0.968 8.3 11.1 287

382249 dscfm 0.968 8.5 10.9 288

382634 dscfm 0.969 8.5 11 290

350788 dscfm 0.981 8.6 10.9 299

351869 dscfm 0.981 8.8 10.8

346185 dscfm 0.981 8.6 11

356026 dscfm 0.95 8.2 11.1 298.8

351530 dscfm 0.95 8 11.5

349893 dscfm 0.95 8.2 11.4

159389 dscfm 1.03 6.3 13.6 281

160974 dscfm 1.03 6.3 13.6 255

192449 dscfm 1.03 6.3 13.6 260

159322 dscfm 0.998 6.3 13.3 285

153342 dscfm 0.998 5.9 13.5 297

191135 dscfm 0.996 6.5 13 296

154995 dscfm 0.996 6.5 13 284

163407 dscfm 0.996 6.5 13 298

170706 dscfm 0.996 6.5 13

209906 dscfm 1.03 7 12.2 254

208009 dscfm 1.03 7 12.2 265

185649 dscfm 1.03 7 12.2 278

183319 dscfm 0.998 7.3 12.2 273

183541 dscfm 0.998 7.1 12.5 280

224995 dscfm 0.996 7.1 12.5 289

178923 dscfm 0.996 7.4 12 293

195476 dscfm 0.996 7.4 12 298

201248 dscfm 0.996 7.4 12

293022 dscfm 0.996 9 10.1 286

274615 dscfm 0.996 9 10.3 294

279612 dscfm 0.996 9 10.3 294

289438 dscfm 0.996 9 10.3 292

0.969 7.3 12.3

Page 76
sampling_runs

0.969 7.6 11.9

0.969 7.8 11.7

0.969 8.5 10.8

0.964 285

0.964 290

0.964 290

0.965 8.4 10.6

0.965 8.4 10.5

0.965 7.5 11.5

0.958 292

0.958 293.5

0.967 291

Page 77
sampling_runs

fg_pressureHg_loi test_methodrun_comments fuel_id fuel_unit_loadfuel_flow_ratefuel_ash fuel_heating_value

0.977 30B

0.9705 30B

30B

0.9705 30B

0.9664 30B

0.9664 30B

0.9664 30B

0.9664 30B

0.961 30B

0.958 30B

0.958 30B

0.958 30B

M5, OTM 028, Method 12 analy Coal sis of M5 filter &probe rinse residue from EPA M5/OTM 28 14.49 13084

M5, OTM 028, Method 12 analy Coal sis of M5 filter &probe rinse residue from EPA M5/OTM 28 14.03 13146

M5, OTM 028, Method 12 analy Coal sis of M5 filter &probe rinse residue from EPA M5/OTM 28 14.51 13049

M5, OTM 028, Method 12 analy Coal sis of M5 filter &probe rinse residue from EPA M5/OTM 28 12.1 13550

M5, OTM 028, Method 12 analy Coal sis of M5 filter &probe rinse residue from EPA M5/OTM 28 11.38 13677

M5, OTM 028, Method 12 analy Coal sis of M5 filter &probe rinse residue from EPA M5/OTM 28 11.45 13672

M5, OTM028, Method 12 analy Coal sis of M5 filter &probe rinseresidue from EPA M5/OTM 28 12.43 13503

M5, OTM028, Method 12 analy Coal sis of M5 filter &probe rinse residue from EPA M5/OTM 28 12.04 13592

M5, OTM028, Method 12 analy Coal sis of M5 filter &probe rinseresidue from EPA M5/OTM 28 11.97 13576

0.989 M5, OTM28 Coal 13.29 13270

0.989 M5, OTM28 Coal 12.82 13337

0.989 M5, OTM28 Coal 13.52 13280

0.952 M5, OTM28 Coal 12.89 13352

0.955 M5, OTM28 Coal 13.06 13311

0.955 M5, OTM28 Coal 14.07 13178

0.999 M5

0.997 M5

1.004 M5

0.969 M5

0.967 M5

0.96 M17

0.967 M17

0.967 M17

0.971 M17

0.999 M5

0.997 M5

0.999 M5

0.97 M5

0.971 M5

0.966 M17

0.966 M17

0.966 M17

0.968 M17

1.01 M17

1.01 M17

1.02 M17

1.03 M17

EPA 1361

0.958 Clean Air Method 8B

Page 78
sampling_runs

0.958 Clean Air Method 8B

0.958 Clean Air Method 8B

0.958 Clean Air Method 8B

10.48 Sorbent Tube, M17 for LOI

10.48 Sorbent Tube, M17 for LOI

10.48 Sorbent Tube, M17 for LOI

EPA 1361

0.954 Clean Air Method 8B

0.954 Clean Air Method 8B

0.954 Clean Air Method 8B

15.09 Sorbent Tube, M17 for LOI

15.09 Sorbent Tube, M17 for LOI

15.09 Sorbent Tube, M17 for LOI

EPA 1361

Page 79
sampling_runs

fuel_sulfur

1.8

1.9

1.8

1.34

1.33

1.41

1.63

1.63

1.69

1.51

1.61

1.39

1.55

1.67

1.69

Page 80
sampling_run_pollutants1

facility_id report_id sampling_port_id run_id pollutant_namconce conc_units conc_ND conc_MDL

3131 SH-184-U1S12 1 PM (Filterable) 0.099 FALSE

3131 SH-184-U1S12 1 PM (Condensable) 0.043 FALSE

3131 SH-184-U1S12 1 Lead (Pb) 7.14 microgram per dry FALSE standard cubic meter (

3131 SH-184-U1S12 2 PM (Filterable) 0.089 FALSE

3131 SH-184-U1S12 2 PM (Condensable) 0.053 FALSE

3131 SH-184-U1S12 2 Lead (Pb) 6.72 microgram per dry FALSE standard cubic meter (

3131 SH-184-U1S12 3 PM (Filterable) 0.071 FALSE

3131 SH-184-U1S12 3 PM (Condensable) 0.039 FALSE

3131 SH-184-U1S12 3 Lead (Pb) 4.51 microgram per dry FALSE standard cubic meter (

3131 SH-184-U2S12 1 PM (Filterable) 0.029 FALSE

3131 SH-184-U2S12 1 PM (Condensable) 0.075 FALSE

3131 SH-184-U2S12 1 Lead (Pb) 3.06 microgram per dry FALSE standard cubic meter (

3131 SH-184-U2S12 2 PM (Filterable) 0.028 FALSE

3131 SH-184-U2S12 2 PM (Condensable)0.06 FALSE

3131 SH-184-U2S12 2 Lead (Pb) 4.44 microgram per dry FALSE standard cubic meter (

3131 SH-184-U2S12 3 PM (Filterable) 0.02 FALSE

3131 SH-184-U2S12 3 PM (Condensable) 0.045 FALSE

3131 SH-184-U2S12 3 Lead (Pb) 3.1 microgram per dry FALSE standard cubic meter (

3131 SH-184 U3-4CS34 1 PM (Filterable) 0.008 FALSE

3131 SH-184 U3-4CS34 1 PM (Condensable) 0.057 FALSE

3131 SH-184 U3-4CS34 1 Lead (Pb) 2.89 microgram per dry FALSE standard cubic meter (

3131 SH-184 U3-4CS34 2 PM (Filterable) 0.009 FALSE

3131 SH-184 U3-4CS34 2 PM (Condensable) 0.071 FALSE

3131 SH-184 U3-4CS34 2 Lead (Pb) 2.73 microgram per dry FALSE standard cubic meter (

3131 SH-184 U3-4CS34 3 PM (Filterable) 0.01 FALSE

3131 SH-184 U3-4CS34 3 PM (Condensable) 0.074 FALSE

3131 SH-184 U3-4CS34 3 Lead (Pb) 2.24 microgram per dry FALSE standard cubic meter (

3131 Sh-185A S12 1 PM (Filterable) 0.182 FALSE

3131 Sh-185A S12 1 PM (Condensable)0.02 FALSE

3131 Sh-185A S12 2 PM (Filterable) 0.133 FALSE

3131 Sh-185A S12 2 PM (Condensable) 0.009 FALSE

3131 Sh-185A S12 3 PM (Filterable) 0.187 FALSE

3131 Sh-185A S12 3 PM (Condensable) 0.007 FALSE

3131 SH-185B S12 1 PM (Filterable) 0.004 FALSE

3131 SH-185B S12 1 PM (Condensable)0.03 FALSE

3131 SH-185B S12 2 PM (Filterable) 0.002 FALSE

3131 SH-185B S12 2 PM (Condensable) 0.009 FALSE

3131 SH-185B S12 3 PM (Filterable) 0.002 FALSE

3131 SH-185B S12 3 PM (Condensable) 0.027 FALSE

3131 Unit 1 Baseline HG S12 1 Particulate-bound Mercury 0.29 microgram per dry (Hgp) FALSE standard cubic meter (

3131 Unit 1 Baseline HG S12 1 Oxidized Mercury (Hg++) 7.69 microgram per dry FALSE standard cubic meter (

3131 Unit 1 Baseline HG S12 1 Elemental Mercury1.38 (Hg0) microgram per dry FALSE standard cubic meter (

3131 Unit 1 Baseline HG S12 1 Total Mercury (Hgt)6.89 microgram per dry FALSE standard cubic meter (

3131 Unit 2 Baseline Hg S12 1 Particulate-bound Mercury 0.39 microgram per dry (Hgp) FALSE standard cubic meter (

3131 Unit 2 Baseline Hg S12 1 Oxidized Mercury (Hg++) 9.36 microgram per dry FALSE standard cubic meter (

3131 Unit 2 Baseline Hg S12 1 Elemental Mercury (Hg0) 2.3 microgram per dry FALSE standard cubic meter (

3131 Unit 2 Baseline Hg S12 1 Total Mercury (Hgt) 10.81 microgram per dry FALSE standard cubic meter (

3131 Unit 3-4 Baseline Hg CS34 1 Particulate-bound Mercury 2.5 microgram per dry (Hgp) FALSE standard cubic meter (

3131 Unit 3-4 Baseline Hg CS34 1 Oxidized Mercury (Hg++) 8.32 microgram per dry FALSE standard cubic meter (

3131 Unit 3-4 Baseline Hg CS34 1 Elemental Mercury3.24 (Hg0) microgram per dry FALSE standard cubic meter (

3131 Unit 3-4 Baseline Hg CS34 1 Total Mercury (Hgt) 10.85 microgram per dry FALSE standard cubic meter (

Page 81
sampling_run_pollutants1

3131 SH-181 S12 1 Total Mercury (Hgt) 13.827 microgram per dry FALSE standard cubic meter (

3131 SH-181 S12 2 Total Mercury (Hgt) 14.091 microgram per dry FALSE standard cubic meter (

3131 SH-181 S12 3 Total Mercury (Hgt) 15.506 microgram per dry FALSE standard cubic meter (

3131 SH-181 S12 4 Total Mercury (Hgt) 16.939 microgram per dry FALSE standard cubic meter (

3131 SH-181A S12 1 Total Mercury (Hgt) 0.762 microgram per dry FALSE standard cubic meter (

3131 SH-181A S12 2 Total Mercury (Hgt) 0.813 microgram per dry FALSE standard cubic meter (

3131 SH-181A S12 3 Total Mercury (Hgt) 0.483 microgram per dry FALSE standard cubic meter (

3131 SH-181A S12 4 Total Mercury (Hgt) 0.827 microgram per dry FALSE standard cubic meter (

3131 SH-181B CS34 1 Total Mercury (Hgt) 22.377 microgram per dry FALSE standard cubic meter (

3131 SH-181B CS34 2 Total Mercury (Hgt) 22.407 microgram per dry FALSE standard cubic meter (

3131 SH-181B CS34 3 Total Mercury (Hgt) 22.387 microgram per dry FALSE standard cubic meter (

3131 SH-181B CS34 4 Total Mercury (Hgt) 22.484 microgram per dry FALSE standard cubic meter (

3131 SH-186 ESP1A IN 1 PM (Filterable) 0.000385 FALSE

3131 SH-186 ESP1A IN 2 PM (Filterable) 0.000343 FALSE

3131 SH-186 ESP1A IN 3 PM (Filterable) 0.000339 FALSE

3131 SH-186 ESP1A IN 4 PM (Filterable) 0.000439 FALSE

3131 SH-186 ESP1A IN 5 PM (Filterable) 0.000597 FALSE

3131 SH-186 ESP1A IN 6 PM (Filterable) 0.000458 FALSE

3131 SH-186 ESP1A IN 7 PM (Filterable) 0.000781 FALSE

3131 SH-186 ESP1A IN 8 PM (Filterable) 0.000379 FALSE

3131 SH-186 ESP1A IN 9 PM (Filterable)0.00057 FALSE

3131 SH-186 ESP1A OUT1 PM (Filterable)0.00023 FALSE

3131 SH-186 ESP1A OUT2 PM (Filterable) 0.000365 FALSE

3131 SH-186 ESP1A OUT3 PM (Filterable) 0.000299 FALSE

3131 SH-186 ESP1A OUT4 PM (Filterable) 0.000378 FALSE

3131 SH-186 ESP1A OUT5 PM (Filterable)0.00045 FALSE

3131 SH-186 ESP1A OUT6 PM (Filterable) 0.000464 FALSE

3131 SH-186 ESP1A OUT7 PM (Filterable) 0.000626 FALSE

3131 SH-186 ESP1A OUT8 PM (Filterable) 0.000412 FALSE

3131 SH-186 ESP1A OUT9 PM (Filterable) 0.000501 FALSE

3131 SH-186 S12 1 PM (Filterable) 3.11E-06 FALSE

3131 SH-186 S12 2 PM (Filterable) 1.58E-06 FALSE

3131 SH-186 S12 3 PM (Filterable) 3.09E-06 FALSE

3131 SH-186 S12 4 PM (Filterable) 1.59E-06 FALSE

3131 Unit 1 Boiler performance AH 1 IN 1 Sulfur Dioxide (SO2) 713.89 parts per million by FALSE volume (dry) (ppmvd)

3131 Unit 1 Boiler performance AH 1 IN 2 Sulfur Dioxide (SO2) 755.95 parts per million by FALSE volume (dry) (ppmvd)

3131 Unit 1 Boiler performance AH 1 IN 3 Sulfur Dioxide (SO2) 796.6 parts per million by FALSE volume (dry) (ppmvd)

3131 Unit 1 Boiler performance AH 1 IN 4 Sulfur Dioxide (SO2) 833.13 parts per million by FALSE volume (dry) (ppmvd)

3131 Unit 1 Boiler performance ESP1B OUT1 Particulate-bound Mercury 0.08 microgram per dry (Hgp) FALSE standard cubic meter (

3131 Unit 1 Boiler performance ESP1B OUT1 Oxidized Mercury (Hg++) 4.62 microgram per dry FALSE standard cubic meter (

3131 Unit 1 Boiler performance ESP1B OUT1 Elemental Mercury1.97 (Hg0) microgram per dry FALSE standard cubic meter (

3131 Unit 1 Boiler performance ESP1B OUT1 Total Mercury (Hgt) 8.005 microgram per dry FALSE standard cubic meter (

3131 Unit 1 Boiler performance ESP1B OUT2 Particulate-bound Mercury 0.06 microgram per dry (Hgp) FALSE standard cubic meter (

3131 Unit 1 Boiler performance ESP1B OUT2 Oxidized Mercury (Hg++) 8.33 microgram per dry FALSE standard cubic meter (

3131 Unit 1 Boiler performance ESP1B OUT2 Elemental Mercury4.11 (Hg0) microgram per dry FALSE standard cubic meter (

3131 Unit 1 Boiler performance ESP1B OUT2 Total Mercury (Hgt) 11.73 microgram per dry FALSE standard cubic meter (

3131 Unit 1 Boiler performance ESP1B OUT3 Particulate-bound Mercury 0.06 microgram per dry (Hgp) FALSE standard cubic meter (

3131 Unit 1 Boiler performance ESP1B OUT3 Oxidized Mercury10.28 (Hg++) microgram per dry FALSE standard cubic meter (

3131 Unit 1 Boiler performance ESP1B OUT3 Elemental Mercury4.69 (Hg0) microgram per dry FALSE standard cubic meter (

3131 Unit 1 Boiler performance ESP1B OUT3 Total Mercury (Hgt) 14.085 microgram per dry FALSE standard cubic meter (

3131 Unit 2 Boiler Performance AH 2 IN 1 Sulfur Dioxide (SO2) 1256.49 parts per million by FALSE volume (dry) (ppmvd)

3131 Unit 2 Boiler Performance AH 2 IN 2 Sulfur Dioxide (SO2) 1307.08 parts per million by FALSE volume (dry) (ppmvd)

Page 82
sampling_run_pollutants1

3131 Unit 2 Boiler Performance AH 2 IN 3 Sulfur Dioxide (SO2) 1283.27 parts per million by FALSE volume (dry) (ppmvd)

3131 Unit 2 Boiler Performance ESP2B OUT1 Particulate-bound Mercury 0.1 microgram per dry (Hgp) FALSE standard cubic meter (

3131 Unit 2 Boiler Performance ESP2B OUT1 Oxidized Mercury (Hg++) 4.82 microgram per dry FALSE standard cubic meter (

3131 Unit 2 Boiler Performance ESP2B OUT1 Elemental Mercury1.82 (Hg0) microgram per dry FALSE standard cubic meter (

3131 Unit 2 Boiler Performance ESP2B OUT1 Total Mercury (Hgt) 6.515 microgram per dry FALSE standard cubic meter (

3131 Unit 2 Boiler Performance ESP2B OUT2 Particulate-bound Mercury 0.22 microgram per dry (Hgp) FALSE standard cubic meter (

3131 Unit 2 Boiler Performance ESP2B OUT2 Oxidized Mercury (Hg++) 3.4 microgram per dry FALSE standard cubic meter (

3131 Unit 2 Boiler Performance ESP2B OUT2 Elemental Mercury1.58 (Hg0) microgram per dry FALSE standard cubic meter (

3131 Unit 2 Boiler Performance ESP2B OUT2 Total Mercury (Hgt) 4.735 microgram per dry FALSE standard cubic meter (

3131 Unit 2 Boiler Performance ESP2B OUT3 Particulate-bound Mercury 0.17 microgram per dry (Hgp) FALSE standard cubic meter (

3131 Unit 2 Boiler Performance ESP2B OUT3 Oxidized Mercury (Hg++) 3.45 microgram per dry FALSE standard cubic meter (

3131 Unit 2 Boiler Performance ESP2B OUT3 Elemental Mercury1.57 (Hg0) microgram per dry FALSE standard cubic meter (

3131 Unit 2 Boiler Performance ESP2B OUT3 Total Mercury (Hgt)4.8 microgram per dry FALSE standard cubic meter (

Page 83
sampling_run_pollutants1

emission_rateemission_rate_units emission_rate_ND emission_rate_MDL emission_factor emission_factor_units emission_factor_ND emission_factor_MDL run_pollutant_comment

283.8 pound per hour (lb/hr) FALSE 0.2418 pound per million British Thermal Unit (lb/MMBtu) FALSE

122.36 pound per hour (lb/hr) FALSE 0.1043 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.00895 pound per hour (lb/hr) FALSE 7.7E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE

246.72 pound per hour (lb/hr) FALSE 0.2179 pound per million British Thermal Unit (lb/MMBtu) FALSE

145.8 pound per hour (lb/hr) FALSE 0.1288 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.00815 pound per hour (lb/hr) FALSE 7.23E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE

213.42 pound per hour (lb/hr) FALSE 0.177 pound per million British Thermal Unit (lb/MMBtu) FALSE

118.42 pound per hour (lb/hr) FALSE 0.0983 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.00591 pound per hour (lb/hr) FALSE 4.87E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE

92.83 pound per hour (lb/hr) FALSE 0.068 pound per million British Thermal Unit (lb/MMBtu) FALSE

241.9 pound per hour (lb/hr) FALSE 0.1772 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.00428 pound per hour (lb/hr) FALSE 3.11E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE

92.56 pound per hour (lb/hr) FALSE 0.0678 pound per million British Thermal Unit (lb/MMBtu) FALSE

195.2 pound per hour (lb/hr) FALSE 0.1431 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.0063 pound per hour (lb/hr) FALSE 4.58E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE

66.35 pound per hour (lb/hr) FALSE 0.0478 pound per million British Thermal Unit (lb/MMBtu) FALSE

146.33 pound per hour (lb/hr) FALSE 0.1054 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.00444 pound per hour (lb/hr) FALSE 3.2E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE

67.67 pound per hour (lb/hr) FALSE 0.0198 pound per million British Thermal Unit (lb/MMBtu) FALSE

456.81 pound per hour (lb/hr) FALSE 0.1338 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.01008 pound per hour (lb/hr) FALSE 3.2E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE

71.77 pound per hour (lb/hr) FALSE 0.0216 pound per million British Thermal Unit (lb/MMBtu) FALSE

567.47 pound per hour (lb/hr) FALSE 0.1704 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.00948 pound per hour (lb/hr) FALSE 2.96E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE

80.93 pound per hour (lb/hr) FALSE 0.0246 pound per million British Thermal Unit (lb/MMBtu) FALSE

586.55 pound per hour (lb/hr) FALSE 0.178 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.00771 pound per hour (lb/hr) FALSE 2.45E-06 pound per million British Thermal Unit (lb/MMBtu) FALSE

547.1 pound per hour (lb/hr) FALSE 0.433 pound per million British Thermal Unit (lb/MMBtu) FALSE

61.3 pound per hour (lb/hr) FALSE 0.049 pound per million British Thermal Unit (lb/MMBtu) FALSE

400.8 pound per hour (lb/hr) FALSE 0.32 pound per million British Thermal Unit (lb/MMBtu) FALSE

27.2 pound per hour (lb/hr) FALSE 0.022 pound per million British Thermal Unit (lb/MMBtu) FALSE

554.5 pound per hour (lb/hr) FALSE 0.444 pound per million British Thermal Unit (lb/MMBtu) FALSE

21.3 pound per hour (lb/hr) FALSE 0.017 pound per million British Thermal Unit (lb/MMBtu) FALSE

13.7 pound per hour (lb/hr) FALSE 0.01 pound per million British Thermal Unit (lb/MMBtu) FALSE

92.2 pound per hour (lb/hr) FALSE 0.07 pound per million British Thermal Unit (lb/MMBtu) FALSE

5.2 pound per hour (lb/hr) FALSE 0.004 pound per million British Thermal Unit (lb/MMBtu) FALSE

26.9 pound per hour (lb/hr) FALSE 0.02 pound per million British Thermal Unit (lb/MMBtu) FALSE

5.9 pound per hour (lb/hr) FALSE 0.005 pound per million British Thermal Unit (lb/MMBtu) FALSE

81.4 pound per hour (lb/hr) FALSE 0.062 pound per million British Thermal Unit (lb/MMBtu) FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

Page 84
sampling_run_pollutants1

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

3685.98 pound per hour (lb/hr) FALSE 5.396 pound per million British Thermal Unit (lb/MMBtu) FALSE

3312.95 pound per hour (lb/hr) FALSE 4.802 pound per million British Thermal Unit (lb/MMBtu) FALSE

3913.78 pound per hour (lb/hr) FALSE 4.745 pound per million British Thermal Unit (lb/MMBtu) FALSE

4199.04 pound per hour (lb/hr) FALSE 6.15 pound per million British Thermal Unit (lb/MMBtu) FALSE

5488.86 pound per hour (lb/hr) FALSE 8.129 pound per million British Thermal Unit (lb/MMBtu) FALSE

5251.22 pound per hour (lb/hr) FALSE 6.5 pound per million British Thermal Unit (lb/MMBtu) FALSE

7261.9 pound per hour (lb/hr) FALSE 11.084 pound per million British Thermal Unit (lb/MMBtu) FALSE

3712.56 pound per hour (lb/hr) FALSE 5.375 pound per million British Thermal Unit (lb/MMBtu) FALSE

5834.88 pound per hour (lb/hr) FALSE 8.086 pound per million British Thermal Unit (lb/MMBtu) FALSE

2896.63 pound per hour (lb/hr) FALSE 3.382 pound per million British Thermal Unit (lb/MMBtu) FALSE

4555.78 pound per hour (lb/hr) FALSE 5.368 pound per million British Thermal Unit (lb/MMBtu) FALSE

3327.53 pound per hour (lb/hr) FALSE 4.393 pound per million British Thermal Unit (lb/MMBtu) FALSE

4153.22 pound per hour (lb/hr) FALSE 5.675 pound per million British Thermal Unit (lb/MMBtu) FALSE

4859.9 pound per hour (lb/hr) FALSE 6.671 pound per million British Thermal Unit (lb/MMBtu) FALSE

6259.29 pound per hour (lb/hr) FALSE 6.868 pound per million British Thermal Unit (lb/MMBtu) FALSE

6715.47 pound per hour (lb/hr) FALSE 9.471 pound per million British Thermal Unit (lb/MMBtu) FALSE

4826.57 pound per hour (lb/hr) FALSE 6.231 pound per million British Thermal Unit (lb/MMBtu) FALSE

6046.19 pound per hour (lb/hr) FALSE 7.581 pound per million British Thermal Unit (lb/MMBtu) FALSE

54.63 pound per hour (lb/hr) FALSE 0.053 pound per million British Thermal Unit (lb/MMBtu) FALSE

26.09 pound per hour (lb/hr) FALSE 0.027 pound per million British Thermal Unit (lb/MMBtu) FALSE

51.84 pound per hour (lb/hr) FALSE 0.053 pound per million British Thermal Unit (lb/MMBtu) FALSE

27.67 pound per hour (lb/hr) FALSE 0.027 pound per million British Thermal Unit (lb/MMBtu) FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

Page 85
sampling_run_pollutants1

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

Page 86
sampling_run_pollutants1

run_pollutant_comment

Page 87
sampling_run_fuel

facility_id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_NDfuel_conc_MDL

3131 SH-184 U3-4CS34 1 Lead (Pb) 7.05 milligram per kilogram (dry FALSE ) (mg/kg)

3131 SH-184 U3-4CS34 2 Lead (Pb) 6.72 milligram per kilogram (dry FALSE ) (mg/kg)

3131 SH-184 U3-4CS34 3 Lead (Pb) 8.08 milligram per kilogram (dry FALSE ) (mg/kg)

3131 SH-184-U1S12 1 Lead (Pb) 4.38 milligram per kilogram (dry FALSE ) (mg/kg)

3131 SH-184-U1S12 2 Lead (Pb) 4.63 milligram per kilogram (dry FALSE ) (mg/kg)

3131 SH-184-U1S12 3 Lead (Pb) 4.97 milligram per kilogram (dry FALSE ) (mg/kg)

3131 SH-184-U2S12 1 Lead (Pb) 5.66 milligram per kilogram (dry FALSE ) (mg/kg)

3131 SH-184-U2S12 2 Lead (Pb) 4.74 milligram per kilogram (dry FALSE ) (mg/kg)

3131 SH-184-U2S12 3 Lead (Pb) 4.66 milligram per kilogram (dry FALSE ) (mg/kg)

Page 88
sampling_run_fuel

fuel_conc_MDL

Page 89