Name: Jim Burger

Title: I&C Supervisor

Company: Spruance Genco, LLC

Sign Date:

Name: Lenny Katerynczuk

Title: Project Manager

Company: AirNova, Inc.

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Spruance Unit 2 MACT ICR Testing

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Wednesday, February 02, 2011 Page 1 of 23
Spruance Unit 2 MACT ICR Testing

Facility Information:

Spruance Genco, LLC

5001 Commerce Road

Richmond VA 23234

Contact: Jim Burger

Phone: (804) 743-9710 ext. 23

Fax:

Email: jim.burger@richmondcogen.com

Testing Company:

AirNova, Inc.

5845 Clayton Avenue

Pennsauken NJ 08109

Contact:Lenny Katerynczuk

Phone: 856-486-1500

Fax: 856-486-9896

Email: lenny@airnova.com

Air Permit Number:

51033

Permitted Source ID/Name:

51033 Spruance Genco, LLC

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 5176000399 FRS #: 110000868865

SCC / Description 10100205 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Traveling Grate (Overfeed) Stoker (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 124 0 0 0 1800 2700 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit Carbon Monoxide Method 10 3 120 0

Organic Condensible 

Particulate

Stack Exit Method 202 3 365 0

Inorganic (Aqueous) 

Condensible Part.

Stack Exit Method 202 3 365 0

Regulation Description Compound Limit Unit

Clean Air Act Section 114 0

Wednesday, February 02, 2011 Page 2 of 23
Spruance Unit 2 MACT ICR Testing

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 180 0

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 190 0

Stack Exit Filterable PM2.5 OTM - 27/28 3 365 0

Stack Exit Lead Method 29 3 360 0

Stack Exit Manganese Method 29 3 360 0

Stack Exit Cadmium Method 29 3 360 0

Stack Exit Antimony Method 29 3 360 0

Stack Exit Nickel Method 29 3 360 0

Stack Exit Beryllium Method 29 3 360 0

Stack Exit Arsenic Method 29 3 360 0

Stack Exit Cobalt Method 29 3 360 0

Stack Exit Chromium Method 29 3 360 0

Stack Exit Selenium Method 29 3 360 0

Stack Exit Filterable Particulate Method 5 3 360 0

Stack Exit Sulfur Dioxide Method 6C 3 180 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0

Wednesday, February 02, 2011 Page 3 of 23
Spruance Unit 2 MACT ICR Testing

Sampling / Stack Data Results Summary

Location Stack Exit - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 202

Average

Run Number 1 2 3

Test Date 4/22/2010 4/22/2010 4/23/2010

Run Start Time 6:47:00 AM 1:35:00 PM 6:00:00 AM

Run Finish Time 1:18:00 PM 7:43:00 PM 12:10:00 PM

Net Run Time, minutes 382 359.2 370.7

Dry Gas Meter Volume Sampled, dscf 133.978 125.697 129.632 129.769

Moisture Content of Stack Gas, % 12.49 12.68 12.06 12.410

Moisture Saturation at Stack Gas Temperature, % 63.07 64.90 65.05 64.340

Carbon Dioxide, % 14.03 14.29 13.7 14.007

Oxygen, % 4.89 4.45 4.97 4.770

Average Stack Gas Temperature, °F 189.50 190.83 191.08 190.470

Dry Volumetric Flow Rate, dry scfm 171,515.5 158,021.1 164,255.8 164,597.467

Actual Wet Volumetric Flue Gas Flow Rate, acfm 242,229.9 224,115.5 230,707.1 232,350.833

Percent Isokinetic of Sampling Rate, % 97.0 105.1 101.0 101.033

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 02, 2011 Page 4 of 23
Spruance Unit 2 MACT ICR Testing

Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Wednesday, February 02, 2011 Page 5 of 23
Spruance Unit 2 MACT ICR Testing

Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack Exit - Method 5

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Wednesday, February 02, 2011 Page 6 of 23
Spruance Unit 2 MACT ICR Testing

Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Wednesday, February 02, 2011 Page 7 of 23
Spruance Unit 2 MACT ICR Testing

Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Wednesday, February 02, 2011 Page 8 of 23
Spruance Unit 2 MACT ICR Testing

Emissions Summary

Location: Stack Exit - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 4.80E-01 2.39E-01 4.23E-01 0.381

ppm 5.27E+02 2.69E+02 4.80E+02 425.333

ppm@7%O2 4.49E+02 2.23E+02 3.95E+02 355.667

Location: Stack Exit - Method 202

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 7.3 13.3 4.4 8.333

lb/mmBtuO2 1.53E-03 2.90E-03 9.60E-04 0.002

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 1.4 1.5 0.9 1.267

lb/mmBtuO2 2.94E-04 3.27E-04 1.96E-04 0.000

Location: Stack Exit - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 2.76E-03 1.52E-03 1.90E-03 0.002

ppm 1.92E+00 1.09E+00 1.37E+00 1.460

ppm@7%O2 1.64E+00 9.05E-01 1.13E+00 1.225

Location: Stack Exit - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.07 0.08 0.07 0.073

lb/mmBtuO2 1.60E-05 1.83E-05 1.66E-05 0.000

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.67 0.7 0.62 0.663

lb/mmBtuO2 1.53E-04 1.60E-04 1.47E-04 0.000

Location: Stack Exit - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.000556 0.001122 0.00068 0.001

lb/mmBtuO2 6.58E-08 1.34E-07 8.15E-08 0.000

Wednesday, February 02, 2011 Page 9 of 23
Spruance Unit 2 MACT ICR Testing

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.003293 0.00251 0.002801 0.003

lb/mmBtuO2 3.90E-07 3.00E-07 3.36E-07 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.000704 0.000607 0.000944 0.001

lb/mmBtuO2 8.33E-08 7.25E-08 1.13E-07 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.000697 0.000413 0.000406 0.001

lb/mmBtuO2 8.25E-08 4.93E-08 4.87E-08 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.009668 0.006127 0.009319 0.008

lb/mmBtuO2 1.14E-06 7.31E-07 1.12E-06 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.00223 0.00225 0.00308 0.003

lb/mmBtuO2 2.64E-07 2.69E-07 3.69E-07 0.000

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.004569 0.004208 0.00477 0.005

lb/mmBtuO2 5.41E-07 5.02E-07 5.72E-07 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.00666 0.00634 0.007121 0.007

lb/mmBtuO2 7.88E-07 7.57E-07 8.54E-07 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.01409 0.029964 0.034765 0.026

lb/mmBtuO2 1.67E-06 3.58E-06 4.17E-06 0.000

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.00137 0.00111 0.0034 0.002

lb/mmBtuO2 1.62E-07 1.32E-07 4.08E-07 0.000

Wednesday, February 02, 2011 Page 10 of 23
Spruance Unit 2 MACT ICR Testing

Process Run Data

Location: Stack Exit - Method 5

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 69.9 57.7 84.8 70.800

lb/mmBtuO2 8.27E-03 6.89E-03 1.02E-02 0.008

Location: Stack Exit - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 6.21E-02 6.78E-02 6.72E-02 0.066

ppm 3.08E+01 3.30E+01 3.15E+01 31.767

ppm@7%O2 2.54E+01 2.77E+01 2.75E+01 26.867

Location: Stack Exit - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 2.90E-01 2.93E-01 2.95E-01 0.293

ppm 2.00E+02 1.99E+02 1.93E+02 197.333

ppm@7%O2 1.65E+02 1.67E+02 1.68E+02 166.667

Location: Stack Exit - OTM - 27/28

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 6 22.7 17.5 15.400

lb/mmBtuO2 1.26E-03 4.95E-03 3.82E-03 0.003

Wednesday, February 02, 2011 Page 11 of 23
Spruance Unit 2 MACT ICR Testing

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input 796 Million Btus/hr 0

2 Heat Input 869 Million Btus/hr 0

2 Steam Output 579 1,000 lb/hr 0

2 Sorbent Injection Rate 15.4 gal/min 0

2 Pressure Drop Across FGD 1.83 in. H2O 0

2 Electrical Generation (Net) 59.09 MWe 0

2 Electrical Generation (Gross) 61.86 MWh 0

3 Heat Input 810 Million Btus/hr 0

3 Steam Output 574 1,000 lb/hr 0

3 Sorbent Injection Rate 14.1 gal/min 0

3 Pressure Drop Across FGD 1.81 in. H2O 0

3 Electrical Generation (Net) 58.48 MWe 0

3 Electrical Generation (Gross) 61.26 MWh 0

1 Steam Output 585 1,000 lb/hr 0

1 Sorbent Injection Rate 14.68 gal/min 0

1 Pressure Drop Across FGD 1.83 in. H2O 0

1 Electrical Generation (Net) 58.56 MWe 0

1 Electrical Generation (Gross) 61.35 MWh 0

4 Heat Input 802 Million Btus/hr 0

4 Steam Output 581 1,000 lb/hr 0

4 Sorbent Injection Rate 13.07 gal/min 0

4 Pressure Drop Across FGD 1.83 in. H2O 0

4 Electrical Generation (Net) 58.51 MWe 0

4 Electrical Generation (Gross) 61.3 MWh 0

5 Heat Input 829 Million Btus/hr 0

5 Steam Output 570 1,000 lb/hr 0

5 Sorbent Injection Rate 13.99 gal/min 0

5 Pressure Drop Across FGD 1.8 in. H2O 0

5 Electrical Generation (Net) 58.25 MWe 0

5 Electrical Generation (Gross) 61.03 MWh 0

6 Heat Input 888 Million Btus/hr 0

6 Steam Output 591 1,000 lb/hr 0

6 Sorbent Injection Rate 9.93 gal/min 0

Wednesday, February 02, 2011 Page 12 of 23
Spruance Unit 2 MACT ICR Testing

APCD Run Data

6 Pressure Drop Across FGD 1.84 in. H2O 0

6 Electrical Generation (Net) 59.35 MWe 0

6 Electrical Generation (Gross) 62.14 MWh 0

7 Heat Input 837 Million Btus/hr 0

7 Steam Output 592 1,000 lb/hr 0

7 Sorbent Injection Rate 10.71 gal/min 0

7 Pressure Drop Across FGD 1.85 in. H2O 0

7 Electrical Generation (Net) 62 MWe 0

7 Electrical Generation (Gross) 592 MWh 0

8 Heat Input 909 Million Btus/hr 0

8 Steam Output 593 1,000 lb/hr 0

8 Sorbent Injection Rate 11.21 gal/min 0

8 Pressure Drop Across FGD 1.86 in. H2O 0

8 Electrical Generation (Net) 59.09 MWe 0

8 Electrical Generation (Gross) 61.85 MWh 0

9 Heat Input 840 Million Btus/hr 0

9 Steam Output 586 1,000 lb/hr 0

9 Sorbent Injection Rate 10.86 gal/min 0

9 Pressure Drop Across FGD 3.58 in. H2O 0

9 Electrical Generation (Net) 43.95 MWe 0

9 Electrical Generation (Gross) 46.96 MWh 0

Run Name Value UOM Comments

Target

Value

1 BAGHOUSE 99.1 % 99.1

2 BAGHOUSE 99.1 % 99.1

3 BAGHOUSE 99.1 % 99.1

4 BAGHOUSE 99.1 % 99.1

5 BAGHOUSE 99.1 % 99.1

6 BAGHOUSE 99.1 % 99.1

7 BAGHOUSE 99.1 % 99.1

8 BAGHOUSE 99.1 % 99.1

9 BAGHOUSE 99.1 % 99.1

1 SCRUBBER 90 % 90

2 SCRUBBER 90 % 90

3 SCRUBBER 90 % 90

Wednesday, February 02, 2011 Page 13 of 23
Spruance Unit 2 MACT ICR Testing

Process Lab Run Data

4 SCRUBBER 90 % 90

5 SCRUBBER 90 % 90

6 SCRUBBER 90 % 90

7 SCRUBBER 90 % 90

8 SCRUBBER 90 % 90

9 SCRUBBER 90 % 90

Wednesday, February 02, 2011 Page 14 of 23
Spruance Unit 2 MACT ICR Testing

Sampling / Stack Data Results Detail

Location Stack Exit - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Wednesday, February 02, 2011 Page 15 of 23
Spruance Unit 2 MACT ICR Testing

Location Stack Exit - Method 202

Average

Run Number 1 2 3

Test Date 4/22/2010 4/22/2010 4/23/2010

Run Start Time 6:47:00 AM 1:35:00 PM 6:00:00 AM

Run Finish Time 1:18:00 PM 7:43:00 PM 12:10:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 382 359.2 370.7

Nozzle Diameter, inches 0.18 0.18 0.18 0.180

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.99 0.99 0.99 0.990

Barometric Pressure, inches of Mercury 29.81 29.81 29.9 29.840

Average Orifice Meter Differential, inches H2O 0.39 0.39 0.39 0.390

Dry Gas Meter Volume Sampled, cubic feet 134.716 129.724 131.008 131.816

Average Dry Gas Meter Temperature, °F 64.17 78.00 68.42 70.197

Dry Gas Meter Volume Sampled, dscf 133.978 125.697 129.632 129.769

Total Moisture Liquid collected, g 406.3 387.9 377.7 390.633

Volume of Water Vapor, standard cubic feet 19.12 18.26 17.78 18.387

Moisture Content of Stack Gas, % 12.49 12.68 12.06 12.410

Moisture Saturation at Stack Gas Temperature, % 63.07 64.90 65.05 64.340

Dry Mole Fraction 0.8751 0.8732 0.8794 0.876

Carbon Dioxide, % 14.03 14.29 13.7 14.007

Oxygen, % 4.89 4.45 4.97 4.770

Carbon Monoxide & Nitrogen, % 81.08 81.26 81.33 81.223

Fuel Factor 1.14 1.15 1.16

Dry Molecular Weight, lb/lb-Mole 30.44 30.46 30.39 30.430

Wet Molecular weight, lb/lb-Mole 28.89 28.88 28.90 28.890

Flue Gas Static Pressure, inches of H2O -0.45 -0.45 -0.45 -0.450

Absolute Flue Gas Pressure, inches of Mercury 29.78 29.78 29.87 29.810

Average Stack Gas Temperature, °F 189.50 190.83 191.08 190.470

Average Velocity Head, inches of H2O 0.5952690318

39693

0.508321156

408159

0.540520392

027564

0.548

Average Stack Gas Velocity, feet/second 48.14 44.54 45.85 46.177

Stack Cross-Sectional Area, square feet 83.863 83.863 83.863 83.863

Dry Volumetric Flow Rate, dry scfm 171,515.5 158,021.1 164,255.8 164,597.467

Actual Wet Volumetric Flue Gas Flow Rate, acfm 242,229.9 224,115.5 230,707.1 232,350.833

Percent Isokinetic of Sampling Rate, % 97.0 105.1 101.0 101.033

Percent Excess Air, % 29.6 26.2 30.1 28.633

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 124 124 124

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 02, 2011 Page 16 of 23
Spruance Unit 2 MACT ICR Testing

Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Wednesday, February 02, 2011 Page 17 of 23
Spruance Unit 2 MACT ICR Testing

Location Stack Exit - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Wednesday, February 02, 2011 Page 18 of 23
Spruance Unit 2 MACT ICR Testing

Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Wednesday, February 02, 2011 Page 19 of 23
Spruance Unit 2 MACT ICR Testing

Location Stack Exit - Method 5

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Wednesday, February 02, 2011 Page 20 of 23
Spruance Unit 2 MACT ICR Testing

Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Wednesday, February 02, 2011 Page 21 of 23
Spruance Unit 2 MACT ICR Testing

Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Wednesday, February 02, 2011 Page 22 of 23
Spruance Unit 2 MACT ICR Testing

Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Wednesday, February 02, 2011 Page 23 of 23