Name:

Title:

Company:

Sign Date:

Name: Mike Taylor

Title: President

Company: Catalyst Air Management

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

KY 1385 Dale Unit 3

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Monday, February 21, 2011 Page 1 of 18
KY 1385 Dale Unit 3

Facility Information:

Dale

1925 Ford Rd.

Ford KY 40320

Contact: Louis Petrey

Phone: 859-745-4157 ext. 204

Fax:

Email: louis.petrey@ekpc.coop

Testing Company:

Catalyst Air Management

2505 Byington-Solway Rd

Knoxville TN 37931

Contact:Mike Taylor

Phone: 865-531-0075

Fax: 831-531-0750

Email: mike.taylor@catalystair.com

Air Permit Number:

1385

Permitted Source ID/Name:

3 William C. Dale Power Station

Permitted Maximum Process Rate:

796.3 mmBtu/hr

Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Dale Unit 3 is a pulverized coal, dry bottom, wall-fired boiler. The unit is equipped with low-Nox burners for Nox 

control and a ESP for PM control.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 110008359542 FRS #: 110008359542

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

KY1385 Dale 

3

147.996 0 0 0 0 0 4 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

KY1385 Dale Carbon Monoxide Method 10 3 120 0

3

KY1385 Dale Formaldehyde Method 0011 3 180 0

3

Total organic compounds 

(TOC) as Propane

KY1385 Dale Method 25A 3 120 0

3

Monday, February 21, 2011 Page 2 of 18
KY 1385 Dale Unit 3

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

KY1385 Dale Hydrogen Fluoride Method 26A 3 180 0

3

KY1385 Dale Hydrogen Chloride Method 26A 3 180 0

3

KY1385 Dale Filterable PM2.5 OTM - 27/28 3 330 0

3

KY1385 Dale Total PM2.5 OTM - 27/28 3 330 0

3

Organic Condensible 

Particulate

KY1385 Dale OTM - 27/28 3 330 0

3

Inorganic (Aqueous) 

Condensible Part.

KY1385 Dale OTM - 27/28 3 330 0

3

KY1385 Dale Antimony Method 29 3 240 0

3

KY1385 Dale Selenium Method 29 3 240 0

3

KY1385 Dale Nickel Method 29 3 240 0

3

KY1385 Dale Lead Method 29 3 240 0

3

KY1385 Dale Filterable Particulate Method 29 3 240 0

3

KY1385 Dale Cobalt Method 29 3 240 0

3

KY1385 Dale Chromium Method 29 3 240 0

3

KY1385 Dale Cadmium Method 29 3 240 0

3

KY1385 Dale Beryllium Method 29 3 240 0

3

KY1385 Dale Arsenic Method 29 3 240 0

3

KY1385 Dale Manganese Method 29 3 240 0

3

Monday, February 21, 2011 Page 3 of 18
KY 1385 Dale Unit 3

Sampling / Stack Data Results Summary

Location KY1385 Dale 3 - Method 0011

Average

Run Number M0011-1 M0011-2 M0011-3

Test Date 4/1/2010 4/1/2010 4/2/2010

Run Start Time 12:27:00 PM 2:54:00 PM 9:48:00 AM

Run Finish Time 2:22:00 PM 4:49:00 PM 11:43:00 AM

Net Run Time, minutes 120 120 120

Dry Gas Meter Volume Sampled, dscf 87.136 90.727 94.828 90.897

Moisture Content of Stack Gas, % 5.92 5.40 5.66 5.660

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.8 10.8 10.3 10.633

Oxygen, % 8.3 8.2 8.6 8.367

Average Stack Gas Temperature, °F 309.63 312.83 293.08 305.180

Dry Volumetric Flow Rate, dry scfm 220,604.6 229,952.3 232,604.6 227,720.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 351,788.8 366,195.7 361,823.5 359,936.000

Percent Isokinetic of Sampling Rate, % 98.9 98.8 102.1 99.933

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location KY1385 Dale 3 - Method 10

Average

Run Number M10-1 M10-2 M10-3

Test Date 4/8/2010 4/8/2010 4/8/2010

Run Start Time 6:10:00 AM 8:20:00 

AM

10:30:00 AM

Run Finish Time 8:10:00 AM 10:20:00 

AM

12:30:00 PM

Carbon Dioxide, % 11 10.6 10.5 10.700

Oxygen, % 8.2 8.6 8.8 8.533

Dry Volumetric Flow Rate, dry scfm 228373 228373 228373 228,373.000

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 6.2 6.2 6.2 6.200

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Monday, February 21, 2011 Page 4 of 18
KY 1385 Dale Unit 3

Location KY1385 Dale 3 - Method 25A

Average

Run Number M25A-1 M25A-2 M25A-3

Test Date 4/8/2010 4/8/2010 4/8/2010

Run Start Time 6:10:00 AM 8:20:00 

AM

10:30:00 AM

Run Finish Time 8:10:00 AM 10:20:00 

AM

12:30:00 PM

Carbon Dioxide, % 11 10.6 10.5 10.700

Oxygen, % 8.2 8.6 8.8 8.533

Dry Volumetric Flow Rate, dry scfm 228373 228373 228373 228,373.000

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 6.2 6.2 6.2 6.200

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location KY1385 Dale 3 - Method 26A

Average

Run Number M26A-1 M26A-2 M26A-3

Test Date 3/31/2010 3/31/2010 4/1/2010

Run Start Time 12:02:00 PM 3:31:00 PM 9:48:00 AM

Run Finish Time 2:54:30 PM 6:23:30 PM 12:40:30 PM

Net Run Time, minutes 180 180 180

Dry Gas Meter Volume Sampled, dscf 131.659 131.151 134.291 132.367

Moisture Content of Stack Gas, % 5.96 5.71 6.15 5.940

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.9 10.8 10.8 10.833

Oxygen, % 8.4 8.4 8.3 8.367

Average Stack Gas Temperature, °F 288.50 299.04 291.96 293.167

Dry Volumetric Flow Rate, dry scfm 222,762.9 219,963.8 223,890.9 222,205.867

Actual Wet Volumetric Flue Gas Flow Rate, acfm 345,624.6 345,051.2 349,566.8 346,747.533

Percent Isokinetic of Sampling Rate, % 98.7 99.5 100.1 99.433

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Monday, February 21, 2011 Page 5 of 18
KY 1385 Dale Unit 3

Location KY1385 Dale 3 - Method 29

Average

Run Number M29-1 M29-2 M29-3

Test Date 4/6/2010 4/6/2010 4/7/2010

Run Start Time 7:02:00 AM 11:29:00 

AM

6:00:00 AM

Run Finish Time 11:12:00 AM 3:40:00 PM 10:09:00 AM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 186.112 180.855 183.182 183.383

Moisture Content of Stack Gas, % 5.65 5.94 6.25 5.947

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.4 10.2 11 10.533

Oxygen, % 8.4 8.5 8.3 8.400

Average Stack Gas Temperature, °F 302.38 313.29 300.79 305.487

Dry Volumetric Flow Rate, dry scfm 232,088.4 227,217.7 227,192.2 228,832.767

Actual Wet Volumetric Flue Gas Flow Rate, acfm 366,195.7 364,762.2 359,888.2 363,615.367

Percent Isokinetic of Sampling Rate, % 100.4 99.6 100.9 100.300

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location KY1385 Dale 3 - OTM - 27/28

Average

Run Number OTM27-1 OTM27-2 OTM27-3

Test Date 4/7/2010 4/7/2010 4/8/2010

Run Start Time 6:53:00 AM 12:40:00 

PM

6:17:00 AM

Run Finish Time 12:03:00 PM 6:15:00 PM 11:52:00 AM

Net Run Time, minutes 299 329.5 329.5

Dry Gas Meter Volume Sampled, dscf 108.494 119.841 122.512 116.949

Moisture Content of Stack Gas, % 6.12 6.23 6.19 6.180

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.4 10.2 11 10.533

Oxygen, % 8.4 8.5 8.3 8.400

Average Stack Gas Temperature, °F 305.92 314.25 298.67 306.280

Dry Volumetric Flow Rate, dry scfm 227,496.7 226,212.9 228,178.7 227,296.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 361,178.4 363,472.0 359,099.8 361,250.067

Percent Isokinetic of Sampling Rate, % 102.1 102.9 104.3 103.100

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Monday, February 21, 2011 Page 6 of 18
KY 1385 Dale Unit 3

Monday, February 21, 2011 Page 7 of 18
KY 1385 Dale Unit 3

Emissions Summary

Location: KY1385 Dale 3 - Method 0011

Compound: Formaldehyde

Average

RunNumber M0011-1 M0011-2 M0011-3

Mass_mg 0.002 0.002 0.002 0.002

lb/mmBtuO2 8.21E-07 7.82E-07 7.73E-07 0.000

ppm 6.49E-04 6.24E-04 5.97E-04 0.001

ppm@7%O2 7.16E-04 6.83E-04 6.75E-04 0.001

Location: KY1385 Dale 3 - Method 10

Compound: Carbon Monoxide

Average

Run M10-1 M10-2 M10-3

lb/mmBtuO2 2.90E-02 3.07E-02 3.01E-02 0.030

ppm 2.48E+01 2.54E+01 2.45E+01 24.900

ppm@7%O2 2.71E+01 2.87E+01 2.81E+01 27.967

Location: KY1385 Dale 3 - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run M25A-1 M25A-2 M25A-3

lb/mmBtuO2 5.93E-03 6.18E-03 6.19E-03 0.006

ppm 3.22E+00 3.25E+00 3.20E+00 3.223

ppm@7%O2 3.52E+00 3.67E+00 3.68E+00 3.623

Location: KY1385 Dale 3 - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber M26A-1 M26A-2 M26A-3

Mass_mg 520 540 530 530.000

lb/mmBtuO2 1.42E-01 1.48E-01 1.41E-01 0.144

Compound: Hydrogen Fluoride

Average

RunNumber M26A-1 M26A-2 M26A-3

Mass_mg 17 16 17 16.667

lb/mmBtuO2 4.65E-03 4.40E-03 4.53E-03 0.005

Location: KY1385 Dale 3 - Method 29

Compound: Antimony

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0078 0.0075 0.008 0.008

lb/mmBtuO2 1.51E-06 1.51E-06 1.56E-06 0.000

Compound: Arsenic

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0288 0.0241 0.0275 0.027

Monday, February 21, 2011 Page 8 of 18
KY 1385 Dale Unit 3

lb/mmBtuO2 5.58E-06 4.84E-06 5.37E-06 0.000

Compound: Beryllium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00447 0.00442 0.00499 0.005

lb/mmBtuO2 8.66E-07 8.88E-07 9.74E-07 0.000

Compound: Cadmium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00184 0.0015 0.0015 0.002

lb/mmBtuO2 3.56E-07 3.01E-07 2.93E-07 0.000

Compound: Chromium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0707 0.0476 0.0437 0.054

lb/mmBtuO2 1.37E-05 9.56E-06 8.53E-06 0.000

Compound: Cobalt

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0169 0.0156 0.0187 0.017

lb/mmBtuO2 3.27E-06 3.13E-06 3.65E-06 0.000

Compound: Filterable Particulate

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 68 92.8 34.8 65.200

lb/mmBtuO2 1.32E-02 1.86E-02 6.79E-03 0.013

Compound: Lead

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.03975 0.0401 0.042 0.041

lb/mmBtuO2 7.70E-06 8.06E-06 8.20E-06 0.000

Compound: Manganese

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0364 0.0265 0.0276 0.030

lb/mmBtuO2 7.05E-06 5.32E-06 5.39E-06 0.000

Compound: Nickel

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0913 0.0381 0.0404 0.057

lb/mmBtuO2 1.77E-05 7.66E-06 7.89E-06 0.000

Compound: Selenium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.6571 0.7156 0.6941 0.689

Monday, February 21, 2011 Page 9 of 18
KY 1385 Dale Unit 3

Process Run Data

lb/mmBtuO2 1.27E-04 1.44E-04 1.36E-04 0.000

Location: KY1385 Dale 3 - OTM - 27/28

Compound: Filterable PM2.5

Average

RunNumber OTM27-1 OTM27-2 OTM27-3

Mass_mg 47.86 39.26 35.26 40.793

lb/mmBtuO2 1.59E-02 1.19E-02 1.03E-02 0.013

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber OTM27-1 OTM27-2 OTM27-3

Mass_mg 35 38 39 37.333

lb/mmBtuO2 1.16E-02 1.15E-02 1.14E-02 0.012

Compound: Organic Condensible Particulate

Average

RunNumber OTM27-1 OTM27-2 OTM27-3

Mass_mg 3.3 6.8 2.4 4.167

lb/mmBtuO2 1.10E-03 2.06E-03 7.01E-04 0.001

Compound: Total PM2.5

Average

RunNumber OTM27-1 OTM27-2 OTM27-3

Mass_mg 86.16 84.06 76.66 82.293

lb/mmBtuO2 2.86E-02 2.55E-02 2.24E-02 0.026

Monday, February 21, 2011 Page 10 of 18
KY 1385 Dale Unit 3

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input Million Btus/million BTU using O2 792 0 March 31, 2010

1 Unit Load 75 MW 0 March 31, 2010

1 Steam Rate 629 1000 lbs/hr 0 March 31, 2010

2 Heat Input Million Btus/million BTU using O2 776 0 April 1, 2010

2 Unit Load 75 MW 0 April 1, 2010

2 Steam Rate 618 1000 lbs/hr 0 April 1, 2010

3 Heat Input Million Btus/million BTU using O2 783 0 April 2, 2010

3 Unit Load 75 MW 0 April 2, 2010

3 Steam Rate 622 1000 lbs/hr 0 April 2, 2010

4 Heat Input Million Btus/million BTU using O2 788 0 April 6, 2010

4 Unit Load 75 MW 0 April 6, 2010

4 Steam Rate 632 1000 lbs/hr 0 April 6, 2010

5 Heat Input Million Btus/million BTU using O2 788 0 April 7, 2010

5 Unit Load 75 MW 0 April 7, 2010

5 Steam Rate 631 1000 lbs/hr 0 April 7, 2010

6 Heat Input Million Btus/million BTU using O2 781 0 April 8, 2010

6 Unit Load 75 MW 0 April 8, 2010

6 Steam Rate 631 1000 lbs/hr 0 April 8, 2010

Run Name Value UOM Comments

Target

Value

1 LOW NOX BURNERS 0 0

2 LOW NOX BURNERS 0 0

3 LOW NOX BURNERS 0 0

4 LOW NOX BURNERS 0 0

5 LOW NOX BURNERS 0 0

6 LOW NOX BURNERS 0 0

1 ELECTROSTATIC PRECIPITATOR 301 Volts 0

2 ELECTROSTATIC PRECIPITATOR 315 Volts 0

3 ELECTROSTATIC PRECIPITATOR 295 Volts 0

4 ELECTROSTATIC PRECIPITATOR 276 Volts 0

5 ELECTROSTATIC PRECIPITATOR 272 Volts 0

6 ELECTROSTATIC PRECIPITATOR 282 Volts 0

Monday, February 21, 2011 Page 11 of 18
KY 1385 Dale Unit 3

Process Lab Run Data

Run Name Value UOM Comments

1 0

Monday, February 21, 2011 Page 12 of 18
KY 1385 Dale Unit 3

Sampling / Stack Data Results Detail

Location KY1385 Dale 3 - Method 0011

Average

Run Number M0011-1 M0011-2 M0011-3

Test Date 4/1/2010 4/1/2010 4/2/2010

Run Start Time 12:27:00 PM 2:54:00 PM 9:48:00 AM

Run Finish Time 2:22:00 PM 4:49:00 PM 11:43:00 AM

Net Traversing Points 24 24 24

Net Run Time, minutes 120 120 120

Nozzle Diameter, inches 0.27 0.27 0.27 0.270

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.01 1.01 1.01 1.010

Barometric Pressure, inches of Mercury 29.1 29.1 29.1 29.100

Average Orifice Meter Differential, inches H2O 1.72 1.85 1.86 1.810

Dry Gas Meter Volume Sampled, cubic feet 93.126 98.172 96.318 95.872

Average Dry Gas Meter Temperature, °F 96.73 103.85 69.29 89.957

Dry Gas Meter Volume Sampled, dscf 87.136 90.727 94.828 90.897

Total Moisture Liquid collected, g 116.5 110.1 120.9 115.833

Volume of Water Vapor, standard cubic feet 5.48 5.18 5.69 5.450

Moisture Content of Stack Gas, % 5.92 5.40 5.66 5.660

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9408 0.946 0.9434 0.943

Carbon Dioxide, % 10.8 10.8 10.3 10.633

Oxygen, % 8.3 8.2 8.6 8.367

Carbon Monoxide & Nitrogen, % 80.9 81 81.1 81.000

Fuel Factor 1.17 1.18 1.19

Dry Molecular Weight, lb/lb-Mole 30.06 30.06 29.99 30.037

Wet Molecular weight, lb/lb-Mole 29.35 29.41 29.31 29.357

Flue Gas Static Pressure, inches of H2O -0.42 -0.42 -0.34 -0.393

Absolute Flue Gas Pressure, inches of Mercury 29.07 29.07 29.08 29.073

Average Stack Gas Temperature, °F 309.63 312.83 293.08 305.180

Average Velocity Head, inches of H2O 0.5178384044

84224

0.559996864

148664

0.559196013

373513

0.546

Average Stack Gas Velocity, feet/second 49.08 51.09 50.48 50.217

Stack Cross-Sectional Area, square feet 119.461 119.461 119.461 119.461

Dry Volumetric Flow Rate, dry scfm 220,604.6 229,952.3 232,604.6 227,720.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 351,788.8 366,195.7 361,823.5 359,936.000

Percent Isokinetic of Sampling Rate, % 98.9 98.8 102.1 99.933

Percent Excess Air, % 63.6 62.2 67.1 64.300

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 147.996 147.996 147.996

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Monday, February 21, 2011 Page 13 of 18
KY 1385 Dale Unit 3

Location KY1385 Dale 3 - Method 10

Average

Run Number M10-1 M10-2 M10-3

Test Date 4/8/2010 4/8/2010 4/8/2010

Run Start Time 6:10:00 AM 8:20:00 AM 10:30:00 AM

Run Finish Time 8:10:00 AM 10:20:00 AM 12:30:00 PM

Carbon Dioxide, % 11 10.6 10.5 10.700

Oxygen, % 8.2 8.6 8.8 8.533

Fuel Factor 1.15 1.16 1.15

Dry Volumetric Flow Rate, dry scfm 228373 228373 228373 228,373.000

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 6.2 6.2 6.2 6.200

Analyzer Make TEI TEI TEI

Analyzer Model 48C 48C 48C

Analyzer Serial Number 48C-71529-

369

48C-71529-

369

48C-71529-

369

Operating Range 200 200 200 200.000

Operating Units ppm ppm ppm

No. Readings/Avg. 60 60 60 60.000

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID CC242679 CC242679 CC242679

Calibration Pre Zero Cylinder Instrument Response 0.41 0.55 0.66 0.540

Calibration Pre Zero Cylinder Bias -0.02 0.05 0.11 0.047

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC307483 CC307483 CC307483

Calibration Pre High Cylinder Instrument Response 94.9 95.1 95.7 95.233

Calibration Pre High Cylinder Bias -0.46 -0.36 -0.05 -0.290

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC242679 CC242679 CC242679

Calibration Post Zero Cylinder Instrument Response 0.55 0.66 0.57 0.593

Calibration Post Zero Cylinder Bias 0.05 0.11 0.06 0.073

Calibration Post Zero Cylinder Drift 0.07 0.06 0.05 0.060

Calibration Post High Cylinder ID CC307483 CC307483 CC307483

Calibration Post High Cylinder Instrument Response 95.1 95.7 96.1 95.633

Calibration Post High Cylinder Bias -0.36 -0.05 0.15 -0.087

Calibration Post High Cylinder Drift 0.1 0.31 0.2 0.203

Cavg 25.3 26.1 25.33 25.577

Cavg Units ppmvd ppmvd ppmvd

Cgas 24.7885 25.3888 24.4854 24.888

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Monday, February 21, 2011 Page 14 of 18
KY 1385 Dale Unit 3

Location KY1385 Dale 3 - Method 25A

Average

Run Number M25A-1 M25A-2 M25A-3

Test Date 4/8/2010 4/8/2010 4/8/2010

Run Start Time 6:10:00 AM 8:20:00 AM 10:30:00 AM

Run Finish Time 8:10:00 AM 10:20:00 AM 12:30:00 PM

Carbon Dioxide, % 11 10.6 10.5 10.700

Oxygen, % 8.2 8.6 8.8 8.533

Fuel Factor 1.15 1.16 1.15

Dry Volumetric Flow Rate, dry scfm 228373 228373 228373 228,373.000

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 6.2 6.2 6.2 6.200

Analyzer Make CAI CAI CAI

Analyzer Model 300M 300M 300M

Analyzer Serial Number 5011002 5011002 5011002 5,011,002.0

00

Operating Range 100 100 100 100.000

Operating Units ppm ppm ppm

No. Readings/Avg. 60 60 60 60.000

Calibration Set 2 2 2 2.000

Calibration Pre Zero Cylinder ID CC242679 CC242679 CC242679

Calibration Pre Zero Cylinder Instrument Response 0.03 0 0.03 0.020

Calibration Pre Zero Cylinder Bias -0.03 -0.13 -0.03 -0.063

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC101331 CC101331 CC101331

Calibration Pre High Cylinder Instrument Response 9.55 9.5 9.52 9.523

Calibration Pre High Cylinder Bias 0 -0.17 -0.1 -0.090

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC242679 CC242679 CC242679

Calibration Post Zero Cylinder Instrument Response 0 0.03 0.06 0.030

Calibration Post Zero Cylinder Bias -0.13 -0.03 0.07 -0.030

Calibration Post Zero Cylinder Drift 0.1 0.1 0.1 0.100

Calibration Post High Cylinder ID CC101331 CC101331 CC101331

Calibration Post High Cylinder Instrument Response 9.5 9.52 9.59 9.537

Calibration Post High Cylinder Bias -0.17 -0.1 0.13 -0.047

Calibration Post High Cylinder Drift 0.17 0.07 0.23 0.157

Cavg 3.03 3.05 3.04 3.040

Cavg Units ppmvw ppmvw ppmvw

Cgas 3.221 3.2475 3.1997 3.223

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Cgasw 3.0213406940

0631

3.046187467

08794

3.001298633

01788

3.023

Cgasw Units ppmvw ppmvw ppmvw

Monday, February 21, 2011 Page 15 of 18
KY 1385 Dale Unit 3

Location KY1385 Dale 3 - Method 26A

Average

Run Number M26A-1 M26A-2 M26A-3

Test Date 3/31/2010 3/31/2010 4/1/2010

Run Start Time 12:02:00 PM 3:31:00 PM 9:48:00 AM

Run Finish Time 2:54:30 PM 6:23:30 PM 12:40:30 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 180 180 180

Nozzle Diameter, inches 0.27 0.27 0.27 0.270

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.01 1.01 1.01 1.010

Barometric Pressure, inches of Mercury 29.1 29.1 29.1 29.100

Average Orifice Meter Differential, inches H2O 1.71 1.68 1.73 1.707

Dry Gas Meter Volume Sampled, cubic feet 136.617 137.379 137.853 137.283

Average Dry Gas Meter Temperature, °F 80.52 85.60 74.75 80.290

Dry Gas Meter Volume Sampled, dscf 131.659 131.151 134.291 132.367

Total Moisture Liquid collected, g 177.5 168.7 186.9 177.700

Volume of Water Vapor, standard cubic feet 8.35 7.94 8.80 8.363

Moisture Content of Stack Gas, % 5.96 5.71 6.15 5.940

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9404 0.9429 0.9385 0.941

Carbon Dioxide, % 10.9 10.8 10.8 10.833

Oxygen, % 8.4 8.4 8.3 8.367

Carbon Monoxide & Nitrogen, % 80.7 80.8 80.9 80.800

Fuel Factor 1.15 1.16 1.17

Dry Molecular Weight, lb/lb-Mole 30.08 30.06 30.06 30.067

Wet Molecular weight, lb/lb-Mole 29.36 29.37 29.32 29.350

Flue Gas Static Pressure, inches of H2O -0.4 -0.3 -0.3 -0.333

Absolute Flue Gas Pressure, inches of Mercury 29.07 29.08 29.08 29.077

Average Stack Gas Temperature, °F 288.50 299.04 291.96 293.167

Average Velocity Head, inches of H2O 0.5140436453

17014

0.505672553

623095

0.523021000

269272

0.514

Average Stack Gas Velocity, feet/second 48.22 48.14 48.77 48.377

Stack Cross-Sectional Area, square feet 119.461 119.461 119.461 119.461

Dry Volumetric Flow Rate, dry scfm 222,762.9 219,963.8 223,890.9 222,205.867

Actual Wet Volumetric Flue Gas Flow Rate, acfm 345,624.6 345,051.2 349,566.8 346,747.533

Percent Isokinetic of Sampling Rate, % 98.7 99.5 100.1 99.433

Percent Excess Air, % 65.1 65.0 63.6 64.567

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 147.996 147.996 147.996

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Monday, February 21, 2011 Page 16 of 18
KY 1385 Dale Unit 3

Location KY1385 Dale 3 - Method 29

Average

Run Number M29-1 M29-2 M29-3

Test Date 4/6/2010 4/6/2010 4/7/2010

Run Start Time 7:02:00 AM 11:29:00 AM 6:00:00 AM

Run Finish Time 11:12:00 AM 3:40:00 PM 10:09:00 AM

Net Traversing Points 24 24 24

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.27 0.27 0.27 0.270

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.01 1.01 1.01 1.010

Barometric Pressure, inches of Mercury 29.05 29.05 29.05 29.050

Average Orifice Meter Differential, inches H2O 1.88 1.79 1.80 1.823

Dry Gas Meter Volume Sampled, cubic feet 192.681 191.579 188.418 190.893

Average Dry Gas Meter Temperature, °F 78.60 90.96 75.00 81.520

Dry Gas Meter Volume Sampled, dscf 186.112 180.855 183.182 183.383

Total Moisture Liquid collected, g 236.8 242.6 259.7 246.367

Volume of Water Vapor, standard cubic feet 11.15 11.42 12.22 11.597

Moisture Content of Stack Gas, % 5.65 5.94 6.25 5.947

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9435 0.9406 0.9375 0.941

Carbon Dioxide, % 10.4 10.2 11 10.533

Oxygen, % 8.4 8.5 8.3 8.400

Carbon Monoxide & Nitrogen, % 81.2 81.3 80.7 81.067

Fuel Factor 1.20 1.22 1.15

Dry Molecular Weight, lb/lb-Mole 30.00 29.97 30.09 30.020

Wet Molecular weight, lb/lb-Mole 29.32 29.26 29.33 29.303

Flue Gas Static Pressure, inches of H2O -0.35 -0.35 -0.3 -0.333

Absolute Flue Gas Pressure, inches of Mercury 29.02 29.02 29.03 29.023

Average Stack Gas Temperature, °F 302.38 313.29 300.79 305.487

Average Velocity Head, inches of H2O 0.5649943081

24668

0.551452536

157572

0.547152428

431069

0.555

Average Stack Gas Velocity, feet/second 51.09 50.89 50.21 50.730

Stack Cross-Sectional Area, square feet 119.461 119.461 119.461 119.461

Dry Volumetric Flow Rate, dry scfm 232,088.4 227,217.7 227,192.2 228,832.767

Actual Wet Volumetric Flue Gas Flow Rate, acfm 366,195.7 364,762.2 359,888.2 363,615.367

Percent Isokinetic of Sampling Rate, % 100.4 99.6 100.9 100.300

Percent Excess Air, % 64.4 65.6 63.8 64.600

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 147.996 147.996 147.996

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Monday, February 21, 2011 Page 17 of 18
KY 1385 Dale Unit 3

Location KY1385 Dale 3 - OTM - 27/28

Average

Run Number OTM27-1 OTM27-2 OTM27-3

Test Date 4/7/2010 4/7/2010 4/8/2010

Run Start Time 6:53:00 AM 12:40:00 PM 6:17:00 AM

Run Finish Time 12:03:00 PM 6:15:00 PM 11:52:00 AM

Net Traversing Points 12 12 12

Net Run Time, minutes 299 329.5 329.5

Nozzle Diameter, inches 0.185 0.185 0.185 0.185

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.02 1.02 1.02 1.020

Barometric Pressure, inches of Mercury 29.15 29.15 29.15 29.150

Average Orifice Meter Differential, inches H2O 0.44 0.44 0.44 0.440

Dry Gas Meter Volume Sampled, cubic feet 110.724 125.111 122.661 119.499

Average Dry Gas Meter Temperature, °F 76.08 88.38 65.92 76.793

Dry Gas Meter Volume Sampled, dscf 108.494 119.841 122.512 116.949

Total Moisture Liquid collected, g 150.2 169.1 171.9 163.733

Volume of Water Vapor, standard cubic feet 7.07 7.96 8.09 7.707

Moisture Content of Stack Gas, % 6.12 6.23 6.19 6.180

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9388 0.9377 0.9381 0.938

Carbon Dioxide, % 10.4 10.2 11 10.533

Oxygen, % 8.4 8.5 8.3 8.400

Carbon Monoxide & Nitrogen, % 81.2 81.3 80.7 81.067

Fuel Factor 1.20 1.22 1.15

Dry Molecular Weight, lb/lb-Mole 30.00 29.97 30.09 30.020

Wet Molecular weight, lb/lb-Mole 29.27 29.22 29.34 29.277

Flue Gas Static Pressure, inches of H2O -0.35 -0.35 -0.35 -0.350

Absolute Flue Gas Pressure, inches of Mercury 29.12 29.12 29.12 29.120

Average Stack Gas Temperature, °F 305.92 314.25 298.67 306.280

Average Velocity Head, inches of H2O 0.5480250968

78219

0.548025096

878219

0.548025096

878219

0.548

Average Stack Gas Velocity, feet/second 50.39 50.71 50.10 50.400

Stack Cross-Sectional Area, square feet 119.461 119.461 119.461 119.461

Dry Volumetric Flow Rate, dry scfm 227,496.7 226,212.9 228,178.7 227,296.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 361,178.4 363,472.0 359,099.8 361,250.067

Percent Isokinetic of Sampling Rate, % 102.1 102.9 104.3 103.100

Percent Excess Air, % 64.4 65.6 63.8 64.600

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 147.996 147.996 147.996

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Monday, February 21, 2011 Page 18 of 18