12586 Federal Register I Vol. 59, No. 52 / Thursday, March 17 , 1994 / Notices

DEPARTMENT OF ENERGY

Office of Energy Efficiency and Renewable Energy

[Case No

. F-067]

Energy Conservation Program for Consumer Products : Decision and Order Granting a Waiver From the Furnace Test Procedure to Goodman Manufacturing Company

AGENCY: Office of Energy Efficiency and Renewable Energy, Department of Energy.

ACTION: Decision and order.

SUMMARY: Notice is given of the Decision and Order (Case No. F-067) granting a Waiver to Goodman Manufacturing Company (Goodman) from the existing Department. of Energy (DOE) test procedure for furnaces. The Department is granting Goodman Petition for Waiver regarding blower time delay in calculation of Annual Fuel Utilization Efficiency (AFUE) for its GMN series central furnaces.

FOR FURTHER INFORMATION CONTACT: Cyrus H. Nasseri, U.S. Department of Energy, Office of Energy Efficiency and Renewable Energy, Mail Station EE-431, Forrestal Building, 1000 Independence Avenue SW., Washington, DC 20585, (202) 586-
7140. . Eugene Margolis, Esq.. U.S. Department of Energy, Office of General Counsel, Mail Station GC-72, Forrestal Building, 1000 Independence Avenue SW., Washington, DC 20585, (202)
586-9507.

SUPPLEMENTARY INFORMATION: In
accordance with 10 CFR 430. 27(g), notice is hereby given of the issuance of the Decision and Order as set out below. In the Decision and Order, Goodman has been granted a Waiver for its GMN series central furnaces, permitting the

company to use an alternate test method in determining AFUE.

Issued in Washington, DC. March 11, 1994. Frank M. Stewart, Jr., Chief of Staff, EnergyEfficiency and Renewable Energy.

Decision and Order

In the Matter of: Goodman Manufacturing Company. (Case No. F-067)

Background
The Energy Conservation Program for Consumer Products (other than automobiles) was established pursuant to the Energy Policy and Conservation Act (EPCA), Public Law 94-163, 89 Stat. 917, as amended by the National Energy

### Federal Register 1 Vol. 59, No. 52 / Thursday, March 17, 1994 / Notices 12587

Conservation Policy Act (NECPA), Public Law 95-619,.92 Stat. 3266, the National Appliance Energy Conservation Act of 1987 (NAECA), Public Law 100-12, the National Appliance Energy Conservation Amendments of 1988 (NAECA 1988), Public Law 100-357, and the Energy Policy Act of 1992 (EPAct), Public Law 102-486, 106 Stat. 2776, which requires DOE to prescribe standardized test procedures to measure the energy consumption of certain consumer products, including furnaces. The intent of the test procedures is to provide a comparable measure of energy consumption that will assist consumers in making purchasing decisions. These test procedures appear at 10 CFR part 430, Subpart B. The Department amended the prescribed test procedures by adding 10 CFR 430.27 to create a waiver process. 45 FR 64108, September 26, 1980. Thereafter, DOE further amended its applicance test procedure waiver process to allow the Assistant Secretary for Energy Efficiency and Renewable Energy (Assistant Secretary) to grant an Interim Waiver from test procedure requirements to manufacturers that have petitioned DOE for a waiver of such prescribed test procedures. 51 FR 42823,
November 26. 1986. The waiver process allows the Assistant Secretary to waive temporarily test procedures for a particular basic model when a petitioner shows that the basic model contains one or more design characteristics which prevent testing according to the prescribed test procedures or when the prescribed test procedures may evaluate the basic model in a manner so unrepresentative of its true energy consumption as to provide materially inaccurate comparative data. Waivers generally remain in effect until final test procedure amendments become effective, resolving the problem that is the subject of the waiver. The Interim Waiver provisions added by the 1986 amendment allow the Assistant Secretary to grant an Interim Waiver when it is determined that the applicant will experience economic hardship if the Application for Interim Waiver is denied, if it appears likely that the Petition for Waiver will be granted, andJor the Assistant Secretary determines that it would be.desirable for public policy reasons to grant immediate relief pending a determination on the Petition for Waiver. An Interim Waiver remains in effect for a period of 180 days or until DOE issues its determination on the Petition for Waiver. whichever is sooner, and may be extended for an additional 180 days, if necessary. Goodman filed a "Petition for Waiver," dated November 29, 1993, in accordance with § 430.27 of 10 CFR part 430. The Department published in the Federal Register on February 23, 1994, Goodman's petition and solicited comments, data and information respecting the petition. 58 FR 8608. Goodman also filed an "Application for Interim Waiver" under section 430.27(g) which DOE granted on February 10, 1994. 58 FR 8608, February 23, No comments were received concerning either the "Petition for Waiver" or the "Interim Waiver." The Department consulted with the Federal Trade Commission (FTC) concerning the Goodman Petition. The FTC did not have any objections to the issuance of the waiver to Goodman.

Assertions and Determinations

Goodman's Petition seeks a waiver from the DOE test provisions that require a 1.5-minute time delay between the ignition of the burner and the starting of the circulating air blower. Goodman requests the allowance to test using a 40-second blower time delay when testing its GMN series central furnaces. Goodman states that since the 40-second delay is indicative of how these models actually operate and since such a delay results in an improvement in efficiency of 0.6 to 1.0 percent, the petition should be granted. Under specific circumstances, the DOE test procedure contains exceptions which allow testing with blower delay times of less than the prescribed 1.5- minute delay. Goodman indicates that it is unable to take advantage of any of these exceptions for its GMN series central furnaces. Since the blower controls incorporated on the Goodman furnaces are designed to impose a 40-second blower delay in every instance of start up, and since the current provisions do not specifically address this type of control, DOE agrees that a waiver should be granted to allow the 40- second blower time delay when testing the Goodman GMN series central furnaces. Accordingly, with regard to testing the GMN series central furnaces, today's Decision and Order exempts Goodman from the existing provisions regarding blower controls and allows testing with the 40-second delay. It is, therefore, ordered, that: (1) The "Petition for Waiver" filed by Goodman Manufacturing Company (Case No. F-067) is hereby granted as set forth in paragraph (2) below, subject to the provisions of paragraphs (3), (4), and (5). (2) Notwithstanding any contrary provisions of Appendix N of 10 CFR. Part 430, Subpart B, Goodman Manufacturing Company, shall be permitted to test its GUN series central furnaces on the basis of the test procedure specified in 10 CFR Part 430, with modifications set forth below. (i) Section 3.0 of Appendix N is deleted and replaced with the following paragraph: 3.0 Test Procedure. Testing and measurements shall be as specified in
section 9 in ANSI/ASHRAE Standard 103-82 with the exception of sections 9.2.2, 9.3.1, and 9.3.2, and the inclusion of the following additional procedures: (ii) Add a new paragraph 3.10 to appendix N as follows: 3.10 Gas- and Oil-Fueled Central Furnaces. The following paragraph is in lieu of the requirement specified in section 9.3.1 of ANSVASHRAE Standard 103-82. After equilibrium conditions are achieved following the cool-down test and the required 'measurements performed, turn on the furnace and measure the flue gas temperature, using the thermocouple grid described above, at 0.5 and 2.5 minutes after the main burner(s) comes on. After the burner start-up, delay the blower start-up by 1. 5'minutes (t-), unless : (1) The furnace employs a single motor to drive the power burner and the indoor air circulating blower, in which

case the burner and blower shall be started together; or (2) the furnace is designed to operate using an unvarying delay time that is other than 1.5 minutes, in which case the fan control shall be permitted to start the blower, or (3) the delay time results in the activation of a temperature safety device which shuts off the burner, in which case the fan control shall be permitted to start the blower. In the latter case, if the fan control is adjustable, set it to start the blower at the highest temperature. If the fan control is permitted to start the blower, measure time delay, (t-), using a stopwatch. Record the measured temperatures. During the heat-up test for oil-fueled furnaces, maintain the draft in the flue pipe within *0.01 inch of water columnof the manufacturer's recommended onperiod draft. (iii) With the exception of the modifications set forth above, Goodman Manufacturing Company shall comply in all respects with the test procedures specified in appendix N of 10 CFR part 430, subpart B. (3) The waiver shall remain in effect from the date of issuance of this Order until DOE prescribes final test procedures appropriate to the GMN12588

, Federal Register / Vol. 59, No. 52 / Thursday, March 17, 1994 / Notices

series central furnaces manufactured by Goodman Manufacturing Company. (4) This Waiver is based upon the presumed validity of statements, allegations, and documentary materials submitted by the petitioner. This Waiver maybe revoked or modified at any time upon a determination that the factual basis underlying the petition is incorrect. (5) Effective March 11, 1994, this Waiver supersedes the Interim Waiver granted the Goodman Manufacturing Company on February 10, 1994. 58 FR8608, February 23,1994 (Case No. F066).
Issued in Washington, DC, March 11, 1994.
Frank M

. Stewart, Jr., Chief of Staff, Energy Efficiency and Renewable Energy.

JFR Doc. 94-6260 Filed 3-16-94; 8:45 am]

BILUN0 CODE 6454-01-P#1