APPENDIX 8B. SUPPLEMENTARY LIFE­CYCLE COST AND PAYBACK

PERIOD RESULTS

TABLE OF CONTENTS

8B.1 INTRODUCTION .........................................................................................................8B­1

8B.2 INTRODUCTION TO UNCERTAINTY AND VARIABILITY .................................8B­1

8B.3 UNCERTAINTY ...........................................................................................................8B­2

8B.4 VARIABILITY..............................................................................................................8B­2

8B.5 APPROACHES TO UNCERTAINTY AND VARIABILITY .....................................8B­2

8B.6 PROBABILITY ANALYSIS AND THE USE OF CRYSTAL BALL.........................8B­3

8B.7 GENERAL SERVICE FLUORESCENT RESULTS....................................................8B­4

8B.7.1 Monte Carlo Results .......................................................................................8B­4

8B.7.1.1 Product Class: 4­foot medium bipin ≤ 4,500K........................................ 8B­4

8B.7.1.2 Product Class: 4­foot T5 miniature bipin high output ≤ 4,500K ........... 8B­13

8B.7.1.3 Product Class: 4­foot T5 miniature bipin standard output ≤ 4,500K..... 8B­14

8B.7.1.4 Product Class: 8­foot single pin slimline ≤ 4,500K............................... 8B­15

8B.7.1.5 Product Class: 8­foot recessed double contact high output ≤ 4,500K ... 8B­19

8B.7.2 Lamp and Ballast Price Scenario Results .....................................................8B­24

8B.7.2.1 Product Class: 4­foot medium bipin ≤ 4,500K...................................... 8B­24

8B.7.2.2 Product Class: 4­foot T5 miniature bipin high output ≤ 4,500K ........... 8B­48

8B.7.2.3 Product Class: 4­foot T5 miniature bipin standard output ≤ 4,500K..... 8B­51

8B.7.2.4 Product Class: 8­foot single pin slimline ≤ 4,500K............................... 8B­54

8B.7.2.5 Product Class: 8­foot recessed double contact HO ≤ 4,500K................ 8B­67

8B.7.3 Electricity Price Trend Case Results.............................................................8B­80

8B.7.3.1 Product Class: 4­foot medium bipin ≤ 4,500K...................................... 8B­80

8B.7.3.2 Product Class: 4­foot T5 miniature bipin high output ≤ 4,500K ........... 8B­97

8B.7.3.3 Product Class: 4­foot T5 miniature bipin standard output ≤ 4,500K... 8B­100

8B.7.3.4 Product Class: 8­foot single pin slimline ≤ 4,500K............................. 8B­103

8B.7.3.5 Product Class: 8­foot recessed double contact HO ≤ 4,500K.............. 8B­112

8B.8 INCANDESCENT REFLECTOR RESULTS...........................................................8B­121

8B.8.1 Monte Carlo Results ...................................................................................8B­121

8B.8.2 Lamp Price Scenario Results......................................................................8B­127

8B.8.3 Operating Hour Scenario Results................................................................8B­140

8B.8.4 Electricity Price Trend Case Results...........................................................8B­146

REFERENCES ......................................................................................................................8B­159

LIST OF TABLES

Table 8B.1 LCC and PBP Monte Carlo Results for a Three­Lamp 4­Foot 40W T12

Medium Bipin System Operating in the Commercial Sector ......................8B­6

Table 8B.2 LCC and PBP Monte Carlo Results for a Three­Lamp 4­Foot 34W T12

Medium Bipin System Operating in the Commercial Sector ......................8B­9

8B­i

EE-2006-STD-0131 COMMENT 37.2
Table 8B.3 LCC and PBP Monte Carlo Results for a Three­Lamp 4­foot 32W T8

Medium Bipin System Operating in the Commercial Sector ....................8B­11

Table 8B.4 LCC and PBP Monte Carlo Results for a Two­Lamp 4­Foot 40W T12

Medium Bipin System Operating in the Residential Sector Using

Average Operating Hours..........................................................................8B­12

Table 8B.5 LCC and PBP Monte Carlo Results for a Two­Lamp 4­Foot 40W T12

Medium Bipin System Operating in the Residential Sector Using High

Operating Hours.........................................................................................8B­13

Table 8B.6 LCC and PBP Monte Carlo Results for a Two­Lamp 4­Foot 54W T5

Miniature Bipin High Output System Operating in the Industrial

Sector .........................................................................................................8B­14

Table 8B.7 LCC and PBP Monte Carlo Results for a Two­Lamp 4­Foot 28W T5

Miniature Bipin Standard Output System Operating in the Commercial

Sector .........................................................................................................8B­15

Table 8B.8 LCC and PBP Monte Carlo Results for a Two­Lamp 8­Foot 75W T12 Single

Pin Slimline System Operating in the Commercial Sector........................8B­16

Table 8B.9 LCC and PBP Monte Carlo Results for a Two­Lamp 8­Foot 60W T12 Single

Pin Slimline System Operating in the Commercial Sector........................8B­17

Table 8B.10 LCC and PBP Monte Carlo Results for a Two­Lamp 8­Foot 59W T8 Single

Pin Slimline System Operating in the Commercial Sector........................8B­19

Table 8B.11 LCC and PBP Monte Carlo Results for a Two­Lamp 8­Foot 110W T12

Recessed Double Contact HO System Operating in the Industrial

Sector .........................................................................................................8B­20

Table 8B.12 LCC and PBP Monte Carlo Results for a Two­Lamp 8­Foot 95W T12

Recessed Double Contact HO System Operating in the Industrial

Sector .........................................................................................................8B­22

Table 8B.13 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Commercial Sector with High Lamp Prices.......8B­25

Table 8B.14 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Commercial Sector with Low Lamp Prices.......8B­28

Table 8B.15 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Commercial Sector with No Ballast Prices........8B­31

Table 8B.16 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin

System Operating in the Commercial Sector with High Lamp Prices.......8B­34

Table 8B.17 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin

System Operating in the Commercial Sector with Low Lamp Prices.......8B­36

Table 8B.18 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin

System Operating in the Commercial Sector with No Ballast Prices........8B­37

Table 8B.19 LCC and PBP Results for a Three­Lamp 4­Foot 32W T8 Medium Bipin

System Operating in the Commercial Sector with High Lamp Prices.......8B­40

Table 8B.20 LCC and PBP Results for a Three­Lamp 4­Foot 32W T8 Medium Bipin

System Operating in the Commercial Sector with Low Lamp Prices.......8B­41

Table 8B.21 LCC and PBP Results for a 3­Lamp 4­foot 32W T8 Medium Bipin System

Operating in the Commercial Sector with No Ballast Price ......................8B­41

8B­ii

EE-2006-STD-0131 COMMENT 37.2
Table 8B.22 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Residential Sector with High Lamp Prices and

Average Operating Hours..........................................................................8B­43

Table 8B.23 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Residential Sector with Low Lamp Prices and

Average Operating Hours..........................................................................8B­44

Table 8B.24 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Residential Sector with No Ballast Price and

Average Operating Hours..........................................................................8B­45

Table 8B.25 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Residential Sector with High Lamp Prices and

High Operating Hours................................................................................8B­46

Table 8B.26 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Residential Sector with Low Lamp Prices and

High Operating Hours................................................................................8B­47

Table 8B.27 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Residential Sector with No Ballast Price and

High Operating Hours................................................................................8B­48

Table 8B.28 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin High

Output System Operating in the Industrial Sector with High Lamp

Prices..........................................................................................................8B­49

Table 8B.29 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin High

Output System Operating in the Industrial Sector with Low Lamp

Prices..........................................................................................................8B­50

Table 8B.30 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin High

Output System Operating in the Industrial Sector with No Ballast Price..8B­51

Table 8B.31 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin Standard

Output System Operating in the Commercial Sector with High Lamp

Prices..........................................................................................................8B­52

Table 8B.32 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin Standard

Output System Operating in the Commercial Sector with Low Lamp

Prices..........................................................................................................8B­53

Table 8B.33 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin Standard

Output System Operating in the Commercial Sector with No Ballast

Price ...........................................................................................................8B­54

Table 8B.34 LCC and PBP Results for a Two­Lamp 8­Foot 75W T12 Single Pin

Slimline System Operating in the Commercial Sector with High Lamp

Prices..........................................................................................................8B­55

Table 8B.35 LCC and PBP Results for a Two­Lamp 8­Foot 75W T12 Single Pin

Slimline System Operating in the Commercial Sector with Low Lamp

Prices..........................................................................................................8B­56

Table 8B.36 LCC and PBP Results for a Two­Lamp 8­Foot 75W T12 Single Pin

Slimline System Operating in the Commercial Sector with No Ballast

Prices..........................................................................................................8B­57

8B­iii

EE-2006-STD-0131 COMMENT 37.2
Table 8B.37 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin

Slimline System Operating in the Commercial Sector with High Lamp

Prices..........................................................................................................8B­58

Table 8B.38 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin

Slimline System Operating in the Commercial Sector with Low Lamp

Prices..........................................................................................................8B­60

Table 8B.39 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin

Slimline System Operating in the Commercial Sector with No Ballast

Price ...........................................................................................................8B­62

Table 8B.40 LCC and PBP Results for a Two­Lamp 8­Foot 59W T8 Single Pin Slimline

System Operating in the Commercial Sector with High Lamp Prices.......8B­64

Table 8B.41 LCC and PBP Results for a Two­Lamp 8­Foot 59W T8 Single Pin Slimline

System Operating in the Commercial Sector with Low Lamp Prices.......8B­66

Table 8B.42 LCC and PBP Results for a Two­Lamp 8­Foot 59W T8 Single Pin Slimline

System Operating in the Commercial Sector with No Ballast Prices........8B­67

Table 8B.43 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double

Contact HO System Operating in the Industrial Sector with High Lamp

Prices..........................................................................................................8B­68

Table 8B.44 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double

Contact HO System Operating in the Industrial Sector with Low Lamp

Prices..........................................................................................................8B­70

Table 8B.45 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double

Contact HO System Operating in the Industrial Sector with No Ballast

Prices..........................................................................................................8B­72

Table 8B.46 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double

Contact HO System Operating in Industrial Sector with High Lamp

Prices..........................................................................................................8B­74

Table 8B.47 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double

Contact HO System Operating in Industrial Sector with Low Lamp

Prices..........................................................................................................8B­76

Table 8B.48 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double

Contact HO System Operating in Industrial Sector with No Ballast

Prices..........................................................................................................8B­78

Table 8B.49 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Commercial Sector under the AEO2008 High

Growth Electricity Price Trend Case .........................................................8B­81

Table 8B.50 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Commercial Sector under the AEO2008 Low

Growth Electricity Price Trend Case .........................................................8B­84

Table 8B.51 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin

System Operating in the Commercial Sector under the AEO2008 High

Growth Electricity Price Trend Case .........................................................8B­87

Table 8B.52 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin

System Operating in the Commercial Sector under the AEO2008 Low

Growth Electricity Price Trend Case .........................................................8B­89

8B­iv

EE-2006-STD-0131 COMMENT 37.2
Table 8B.53 LCC and PBP Results for a Three­Lamp 4­Foot 32W T8 Medium Bipin

System Operating in the Commercial Sector under the AEO2008 High

Growth Electricity Price Trend Case .........................................................8B­91

Table 8B.54 LCC and PBP Results for a Three­Lamp 4­Foot 32W T8 Medium Bipin

System Operating in the Commercial Sector under the AEO2008 Low

Growth Electricity Price Trend Case .........................................................8B­92

Table 8B.55 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Residential Sector under the AEO2008 High

Growth Electricity Price Trend Case and Average Operating Hours........8B­93

Table 8B.56 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Residential Sector under the AEO2008 Low

Growth Electricity Price Trend Case and Average Operating Hours........8B­94

Table 8B.57 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Residential Sector under the AEO2008 High

Growth Electricity Price Trend Case and High Operating Hours..............8B­95

Table 8B.58 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin

System Operating in the Residential Sector under the AEO2008 Low

Growth Electricity Price Trend Case and High Operating Hours..............8B­96

Table 8B.59 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin High

Output System Operating in the Industrial Sector under the AEO2008

High Growth Electricity Price Trend Case ................................................8B­98

Table 8B.60 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin High

Output System Operating in the Industrial Sector under the AEO2008

Low Growth Electricity Price Trend Case.................................................8B­99

Table 8B.61 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin Standard

Output System Operating in the Commercial Sector under the

AEO2008 High Electricity Price Trend Case...........................................8B­101

Table 8B.62 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin Standard

Output System Operating in the Commercial Sector under the

AEO2008 Low Growth Electricity Price Trend Case..............................8B­102

Table 8B.63 LCC and PBP Results for a Two­Lamp 8­Foot 75W T12 Single Pin

Slimline System Operating in the Commercial Sector under the

AEO2008 High Growth Electricity Price Trend Case .............................8B­104

Table 8B.64 LCC and PBP Results for a Two­Lamp 8­Foot 75W T12 Single Pin

Slimline System Operating in the Commercial Sector under the

AEO2008 Low Growth Electricity Price Trend Case..............................8B­105

Table 8B.65 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin

Slimline System Operating in the Commercial Sector under the

AEO2008 High Growth Electricity Price Trend Case .............................8B­106

Table 8B.66 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin

Slimline System Operating in the Commercial Sector under the

AEO2008 Low Growth Electricity Price Trend Case..............................8B­108

Table 8B.67 LCC and PBP Results for a Two­Lamp 8­Foot 59W T8 Single Pin Slimline

System Operating in the Commercial Sector under the AEO2008 High

Growth Electricity Price Trend Case .......................................................8B­110

8B­v

EE-2006-STD-0131 COMMENT 37.2
Table 8B.68 LCC and PBP Results for a Two­Lamp 8­Foot 59W T8 Single Pin Slimline

System Operating in the Commercial Sector under the AEO2008 Low

Growth Electricity Price Trend Case .......................................................8B­111

Table 8B.69 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double

Contact HO System Operating in the Industrial Sector under the

AEO2008 High Growth Electricity Price Trend Case .............................8B­113

Table 8B.70 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double

Contact HO System Operating in the Industrial Sector under the

AEO2008 Low Growth Electricity Price Trend Case..............................8B­115

Table 8B.71 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double

Contact HO System Operating in Industrial Sector under the AEO2008

High Growth Electricity Price Trend Case ..............................................8B­117

Table 8B.72 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double

Contact HO System Operating in Industrial Sector under the AEO2008

Low Growth Electricity Price Trend Case...............................................8B­119

Table 8B.73 LCC and PBP Monte Carlo Results for a 90W PAR38 Lamp Operating in

the Commercial Sector.............................................................................8B­122

Table 8B.74 LCC and PBP Monte Carlo Results for a 90W PAR38 Lamp Operating in

the Residential Sector ..............................................................................8B­123

Table 8B.75 LCC and PBP Monte Carlo Results for a 75W PAR38 Lamp Operating in

the Commercial Sector.............................................................................8B­124

Table 8B.76 LCC and PBP Monte Carlo Results for a 75W PAR38 Lamp Operating in

the Residential Sector ..............................................................................8B­125

Table 8B.77 LCC and PBP Monte Carlo Results for a 50W PAR30 Lamp Operating in

the Commercial Sector.............................................................................8B­126

Table 8B.78 LCC and PBP Monte Carlo Results for a 50W PAR30 Lamp Operating in

the Residential Sector ..............................................................................8B­127

Table 8B.79 LCC and PBP Results for a 90W PAR38 Lamp Operating in the

Commercial Sector with High Lamp Prices ............................................8B­128

Table 8B.80 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Residential

Sector with High Lamp Prices.................................................................8B­130

Table 8B.81 LCC and PBP Results for a 90W PAR38 Lamp Operating in the

Commercial Sector with Low Lamp Prices.............................................8B­131

Table 8B.82 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Residential

Sector with Low Lamp Prices..................................................................8B­132

Table 8B.83 LCC and PBP Results for a 75W PAR38 Lamp Operating in the

Commercial Sector using High Lamp Prices...........................................8B­133

Table 8B.84 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Residential

Sector using High Lamp Prices................................................................8B­134

Table 8B.85 LCC and PBP Results for a 75W PAR38 Lamp Operating in the

Commercial Sector using Low Lamp Prices ...........................................8B­135

Table 8B.86 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Residential

Sector using Low Lamp Prices................................................................8B­136

Table 8B.87 LCC and PBP Results for a 50W PAR30 Lamp Operating in the

Commercial Sector using High Lamp Prices...........................................8B­137

8B­vi

EE-2006-STD-0131 COMMENT 37.2
Table 8B.88 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Residential

Sector using High Lamp Prices................................................................8B­138

Table 8B.89 LCC and PBP Results for a 50W PAR30 Lamp Operating in the

Commercial Sector using Low Lamp Prices ...........................................8B­139

Table 8B.90 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Residential

Sector using Low Lamp Prices................................................................8B­140

Table 8B.91 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Residential

Sector using High Operating Hours.........................................................8B­141

Table 8B.92 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Residential

Sector using Low Operating Hours..........................................................8B­142

Table 8B.93 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Residential

Sector using High Operating Hours.........................................................8B­143

Table 8B.94 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Residential

Sector using Low Operating Hours..........................................................8B­144

Table 8B.95 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Residential

Sector using High Operating Hours.........................................................8B­145

Table 8B.96 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Residential

Sector using Low Operating Hours..........................................................8B­146

Table 8B.97 LCC and PBP Results for a 90W PAR38 Lamp Operating in the

Commercial Sector under the AEO2008 High Growth Electricity Price

Trend Case ...............................................................................................8B­147

Table 8B.98 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Residential

Sector under the AEO2008 High Growth Electricity Price Trend Case ..8B­148

Table 8B.99 LCC and PBP Results for a 90W PAR38 Lamp Operating in the

Commercial Sector under the AEO2008 Low Growth Electricity Price

Trend Case ...............................................................................................8B­149

Table 8B.100 LCC and PBP Results for a 90W PAR38 Lamp Operating in the

Residential Sector under the AEO2008 Low Growth Electricity Price

Trend Case ...............................................................................................8B­150

Table 8B.101 LCC and PBP Results for a 75W PAR38 Lamp Operating in the

Commercial Sector under the AEO2008 High Growth Electricity Price

Trend Case ...............................................................................................8B­151

Table 8B.102 LCC and PBP Results for a 75W PAR38 Lamp Operating in the

Residential Sector under the AEO2008 High Growth Electricity Price

Trend Case ...............................................................................................8B­152

Table 8B.103 LCC and PBP Results for a 75W PAR38 Lamp Operating in the

Commercial Sector under the AEO2008 Low Growth Electricity Price

Trend Case ...............................................................................................8B­153

Table 8B.104 LCC and PBP Results for a 75W PAR38 Lamp Operating in the

Residential Sector under the AEO2008 Low Growth Electricity Price

Trend Case ...............................................................................................8B­154

Table 8B.105 LCC and PBP Results for a 50W PAR30 Lamp Operating in the

Commercial Sector under the AEO2008 High Growth Electricity Price

Trend Case ...............................................................................................8B­155

8B­vii

EE-2006-STD-0131 COMMENT 37.2
Table 8B.106 LCC and PBP Results for a 50W PAR30 Lamp Operating in the

Residential Sector under the AEO2008 High Growth Electricity Price

Trend Case ...............................................................................................8B­156

Table 8B.107 LCC and PBP Results for a 50W PAR30 Lamp Operating in the

Commercial Sector under the AEO2008 Low Growth Electricity Price

Trend Case ...............................................................................................8B­157

Table 8B.108 LCC and PBP Results for a 50W PAR30 Lamp Operating in the

Residential Sector under the AEO2008 Low Growth Electricity Price

Trend Case ...............................................................................................8B­158

8B­viii

EE-2006-STD-0131 COMMENT 37.2
APPENDIX 8B. SUPPLEMENTARY LIFE­CYCLE COST AND PAYBACK PERIOD

RESULTS

8B.1 INTRODUCTION

This appendix discusses uncertainty and variability analyses and presents results of those

uncertainty and variability analyses preformed in the life cycle cost (LCC) and payback period

(PBP) analysis. Results for the life cycle cost and payback period analysis using a distribution of

operating hours, discount rates, sales tax, and electricity prices are presented. The average LCC

savings at each efficacy level (EL) for each lamp or lamp­and­ballast design are given as well as

the percentage of consumers who would experience a net benefit or net loss by purchasing a

standards case design instead of a base case design. The median and mean PBP are also given.

This appendix also presents results of the LCC and PBP analysis using high and low lamp prices.

For general service fluorescent lamps (GSFL), results using medium­range lamp prices and no

ballast price, where the price of the ballasts is equal to zero, are also presented. For residential

incandescent reflector lamps (IRL), results using high operating hours (1,210 hours/year: the

average operating hours of a lamp placed in the kitchen of a single­family detached home) and

low operating hours (183 hours/year: the average operating hours of a lamp placed in a closet of

a multi­family 2­4 unit home) are presented. These operating hours are obtained from the U.S.

Lighting Market Characterization: Volume I.i Finally, this appendix presents the LCC and PBP

analysis results based on the Energy Information Administration’s (EIA’s) Annual Energy

Outlook 2008 (AEO2008) high and low growth electricity price trend cases.

8B.2 INTRODUCTION TO UNCERTAINTY AND VARIABILITY

Analysis of an energy­efficiency standard involves calculations of impacts, for example,

the impact of a standard on consumer LCC. In order to perform the calculation, the analyst must

first: 1) specify the equation or model that will be used; 2) define the quantities in the equation;

and 3) provide numerical values for each quantity. In the simplest case, the equation is

unambiguous (contains all relevant quantities and no others), each quantity has a single

numerical value, and the calculation results in a single value. However, certainty and precision

are rarely the case. In almost all cases, the model and/or the numerical values for each quantity

in the model are not completely known (i.e., there is uncertainty) or the model and/or the

numerical values for each quantity in the model depend upon other conditions (i.e., there is

variability).

Thorough analysis involves accounting for uncertainty and variability. While the

simplest analysis involves a single numerical value for each quantity in a calculation, arguments

can arise about what the appropriate value is for each quantity. Explicit analysis of uncertainty

and variability is intended to provide more complete information to the decision­making process.

8B­1

EE-2006-STD-0131 COMMENT 37.2
8B.3 UNCERTAINTY

When making observations of past events or speculating about the future, imperfect

knowledge is the rule rather than the exception. For example, the energy actually consumed by a

particular appliance type (such as the average U.S. lamp) is not directly recorded, but rather

estimated based upon available information. Even direct laboratory measurements have some

margin of error. When estimating numerical values expected for quantities at some future date,

the exact outcome is rarely known in advance.

8B.4 VARIABILITY

Variability means that different applications or situations produce different numerical

values when calculating a quantity. Specifying an exact value for a quantity may be difficult

because the value depends on something else. For example, the number of hours a lamp is

operated by a household depends upon the specific circumstances and behaviors of the occupants

(e.g., number of persons, personal habits about how much light the person needs, etc.).

Variability makes specifying an appropriate population value more difficult in as much as any

one value may not be representative of the entire population. Surveys can be helpful here, and

analysis of surveys can relate the variable of interest (e.g., hours of use) to other variables that

are better known or easier to forecast (e.g., persons per household).

8B.5 APPROACHES TO UNCERTAINTY AND VARIABILITY

This section describes two approaches to uncertainty and variability:

• scenario analysis, and

• probability analysis.

Scenario analysis uses a single numerical value for each quantity in a calculation, then

changes one (or more) of the numerical values and repeats the calculation. A number of

calculations are done, which provide some indication of the extent to which the result depends

upon the assumptions. For example, the life­cycle cost of a lamp could be calculated for energy

rates of 2, 8, and 14¢ per kWh.

The advantages of scenario analysis are that each calculation is simple; a range of

estimates is used; and crossover points can be identified. (An example of a crossover point is the

energy rate above which the life­cycle cost is reduced, holding all other inputs constant. That is,

the crossover point is the energy rate at which the consumer achieves savings in operating

expense that more than compensate for the increased purchase expense.) The disadvantage of

scenario analysis is that there is no information about the likelihood of each scenario.

Probability analysis considers the probabilities within a range of values. For quantities

with variability (e.g., electricity rates in different households), surveys can be used to generate a

8B­2

EE-2006-STD-0131 COMMENT 37.2
frequency distribution of numerical values (e.g., the number of households with electricity rates

at particular levels) to estimate the probability of each value. For quantities with uncertainty,

statistical or subjective measures can be used to provide probabilities (e.g., manufacturing cost to

improve energy efficiency to some level may be estimated to be $10 ± $3).

The major disadvantage of the probability approach is that it requires more information,

namely information about the shapes and magnitudes of the variability and uncertainty of each

quantity. The advantage of the probability approach is that it provides greater information about

the outcome of the calculations, that is, it provides the probability that the outcome will be in a

particular range.

Scenario and probability analysis provide some indication of the robustness of the policy

given the uncertainties and variability. A policy is robust when the impacts are acceptable over a

wide range of possible conditions.

8B.6 PROBABILITY ANALYSIS AND THE USE OF CRYSTAL BALL

To quantify the uncertainty and variability that exist in inputs to the engineering, LCC,

and payback period analyses, the DOE used Microsoft Excel spreadsheets combined with Crystal

Ball, a commercially available add­in, to conduct probability analyses. The probability analyses

used Monte Carlo simulation and probability distributions.

Simulation refers to any analytical method meant to imitate a real­life system, especially

when other analyses are too mathematically complex or too difficult to reproduce. Without the

aid of simulation, a spreadsheet model will only reveal a single outcome, generally the most

likely or average scenario. Spreadsheet risk analysis uses both a spreadsheet model and

simulation to automatically analyze the effect of varying inputs on outputs of the modeled

system. One type of spreadsheet simulation is Monte Carlo simulation, which randomly

generates values for uncertain variables again and again to simulate a system. Monte Carlo

simulation was named for Monte Carlo, Monaco, where the primary attractions are casinos

containing games of chance. Games of chance, such as roulette wheels, dice, and slot machines,

exhibit random behavior. The random behavior in games of chance is similar to how Monte

Carlo simulation utilizes variable values at random to simulate a model. For example, one knows

that a rolled die will present a 1, 2, 3, 4, 5, or 6 after coming to rest, but one does not know

which value will be presented on any particular roll. It is the same with the variables that have a

known range of values but an uncertain value for any particular time or event (e.g., equipment

lifetime, discount rate, and installation cost).

For each uncertain variable (one that has a range of possible values), possible values are defined

with a probability distribution. The type of distribution selected is based on the conditions

surrounding that variable. Probability distribution types include:

8B­3

EE-2006-STD-0131 COMMENT 37.2
NORMAL TRIANGULAR UNIFORM

Figure 8B.6.1 Normal Probability

Distribution

Figure 8B.6.2 Triangular

Probability Distribution

Figure 8B.6.3 Uniform Probability

Distribution

During a simulation, multiple scenarios of a model are calculated by repeatedly sampling values

from the probability distributions for the uncertain variables and using those values in the

simulation. Crystal Ball simulations can consist of as many trials (or scenarios) as desired—

hundreds or even thousands. During a single trial, Crystal Ball randomly selects a value from the

defined possibilities (the range and shape of the probability distribution) for each uncertain

variable and then recalculates the spreadsheet.

8B.7 GENERAL SERVICE FLUORESCENT RESULTS

DOE analyzed five product classes for GSFL: 4­foot medium bipin, 4­foot T5 miniature

bipin standard output, 4­foot T5 miniature bipin high output, 8­foot single­pin slimline, and 8­

foot recessed double contact high­output, all with a correlated color temperature (CCT) less than

or equal to 4,500 Kelvin (K). For each of the five product classes, DOE conducted both

probability analyses (based on Monte Carlo runs) and scenario analyses.

8B.7.1 Monte Carlo Results

To characterize the LCC savings and Monte Carlo results for GSFL, DOE developed

tables to describe the distributions of the results. These tables document the average LCC

savings and percentages of building analyzed with positive and negative LCC savings for various

systems in each event analyzed. In addition, to characterize the distribution of payback periods,

DOE reports the median and average payback period for each system analyzed for each event.

8B.7.1.1 Product Class: 4­foot medium bipin ≤ 4,500K

For the 4­foot medium bipin product class with CCT less than or equal to 4,500K in the

commercial sector, DOE analyzed three baseline lamps: a 40W T12, 34W T12, and 32W T8.

Each lamp was analyzed at five efficacy levels with minimum efficacy requirements of 78, 81,

84, 89, and 94 lm/W. The following tables present the LCC savings and PBP Monte Carlo

results for the three 4­foot medium bipin baselines operating in the commercial sector. Key

inputs consist of using the AEO2008 reference case electricity prices, and medium­range lamp

and ballast prices. Note: Lamp replacement results in Event I are not shown for a 34W T12 lamp

because there are no energy saving lamp replacement options.

8B­4

EE-2006-STD-0131 COMMENT 37.2
8B­5

EE-2006-STD-0131 COMMENT 37.2
Table 8B.1 LCC and PBP Monte Carlo Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System 

Commercial Sector

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option1

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 78.0 41 W T12 & 0.95 BF Mag N/A N/A N/A 

A: Lamp

Replacement EL3 91.2 34 W T12 & 0.88 BF Mag 21.61 100.0 0.0 

EL1 80.5 41 W T12 & 0.88 BF Elec ­6.07 24.0 76.0 

EL1 82.9 41 W T12 & 0.87 BF Elec ­6.83 23.6 76.4 EL2 86.2 32.5 W T8 & 1.18 BF Elec ­6.23 21.4 78.6 

Event I: Lamp

Failure B: Lamp &

Ballast

Replacement

EL2 87.8 41 W T12 & 0.87 BF Elec ­7.09 23.1 76.9 

EL3 91.2 34 W T12 & 0.88 BF Elec 15.05 82.9 17.1 

EL3 90.8 32.5 W T8 & 1 BF Elec 13.33 84.3 15.7 

EL4 92.3 32.5 W T8 & 0.88 BF Elec 34.23 99.7 0.3 EL4 93.8 30.4 W T8 & 1 BF Elec 22.15 94.6 5.4 EL4 93.0 26.6 W T8 & 1.18 BF Elec 26.70 96.4 3.6 

EL5 95.4 32.5 W T8 & 0.88 BF Elec 32.84 99.4 0.6 

EL5 96.0 28.4 W T8 & 1 BF Elec 29.74 98.2 1.8 

Throughout the GSFL results tables, descriptions such as “40W T12 & 0.95 BF Mag” are used. The first term (e.g., 40W) is the rated 

lamp diameter (e.g., T12), the third is the ballast factor of the ballast (e.g., 0.95 BF), and the fourth is the ballast type (e.g., “Mag” for M

Electronic).

8B­6

1

EE-2006-STD-0131 COMMENT 37.2
Table 8B.1 LCC and PBP Monte Carlo Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System 

Commercial Sector (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 78.0 41 W T12 & 0.95 BF Mag N/A N/A N/A 

EL1 80.5 41 W T12 & 0.88 BF Elec ­14.30 12.0 88.0 

EL1 82.9 41 W T12 & 0.87 BF Elec ­15.06 11.7 88.3 

EL2 86.2 32.5 W T8 & 1.18 BF Elec ­14.46 7.0 93.0 EL2 87.8 41 W T12 & 0.87 BF Elec ­15.32 11.1 88.9 

Event II:

Standards

Induced Retrofit

Lamp & Ballast

Replacement

EL3 91.2 34 W T12 & 0.88 BF Elec 6.82 57.1 42.9 

EL3 90.8 32.5 W T8 & 1 BF Elec 5.10 55.0 45.0 

EL4 92.3 32.5 W T8 & 0.88 BF Elec 26.00 96.3 3.7 EL4 93.8 30.4 W T8 & 1 BF Elec 13.92 79.9 20.1 EL4 93.0 26.6 W T8 & 1.18 BF Elec 18.47 86.7 13.3 

EL5 95.4 32.5 W T8 & 0.88 BF Elec 24.61 95.8 4.2 

EL5 96.0 28.4 W T8 & 1 BF Elec 21.51 90.5 9.5 

Baseline Baseline 78.0 41 W T12 & 0.88 BF Elec N/A N/A N/A 

EL1 80.5 41 W T12 & 0.87 BF Elec ­5.65 0.0 100.0 

EL1 82.9 41 W T12 & 0.87 BF Elec ­7.38 0.0 100.0 EL2 87.8 41 W T12 & 0.87 BF Elec ­7.64 0.0 100.0 

Event III: Ballast

Failure Lamp & Ballast

Replacement

EL3 91.2 34 W T12 & 0.88 BF Elec 14.50 100.0 0.0 

EL3 90.8 32.5 W T8 & 1 BF Elec 12.78 100.0 0.0 

EL4 92.3 32.5 W T8 & 0.88 BF Elec 33.68 100.0 0.0 EL4 93.8 30.4 W T8 & 1 BF Elec 21.60 100.0 0.0 EL4 93.0 26.6 W T8 & 1.18 BF Elec 26.15 100.0 0.0 

EL5 95.4 32.5 W T8 & 0.88 BF Elec 32.29 100.0 0.0 

EL5 96.0 28.4 W T8 & 1 BF Elec 29.19 100.0 0.0 

* Comparative lumens are sometimes non­zero for baseline T12 electronic systems under events III and IV (ballast failure and retrofit) 

package is compared to a system with a T12 magnetic ballast. DOE chose to compare these systems for these events because it recogn

regulations will prohibit the use of magnetic ballasts, future purchasers may still seek the current lumen package delivered by current T

8B­7

EE-2006-STD-0131 COMMENT 37.2
Table 8B.1 LCC and PBP Monte Carlo Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System 

Commercial Sector (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline/EL2 86.2 32.5 W T8 & 1.18 BF Elec N/A N/A N/A 

EL3 91.2 34 W T12 & 0.88 BF Elec 21.27 100.0 0.0 

EL3 90.8 32.5 W T8 & 1 BF Elec 19.55 100.0 0.0 

Event IV: Ballast EL4 92.3 32.5 W T8 & 0.88 BF Elec 40.45 100.0 0.0 

Retrofit Lamp & Ballast

Replacement EL4 93.8 30.4 W T8 & 1 BF Elec 28.38 100.0 0.0 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 32.92 100.0 0.0 

EL5 95.4 32.5 W T8 & 0.88 BF Elec 39.07 100.0 0.0 

EL5 96.0 28.4 W T8 & 1 BF Elec 35.96 100.0 0.0 

8B­8

EE-2006-STD-0131 COMMENT 37.2
Table 8B.2 LCC and PBP Monte Carlo Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin System 

Commercial Sector

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 77.9 34 W T12 & 0.88 BF Mag N/A N/A N/A 

EL1 82.4 34 W T12 & 0.88 BF Elec ­10.03 12.9 87.1 

EL2 85.3 34 W T12 & 0.86 BF Elec ­15.11 7.1 92.9 

EL2 86.2 32.5 W T8 & 0.88 BF Elec 3.62 57.6 42.4 

Event I: Lamp

Failure

B: Lamp &

EL3 90.8 32.5 W T8 & 0.78 BF Elec 13.20 85.6 14.4 

EL3 91.2 34 W T12 & 0.86 BF Elec ­15.39 7.2 92.8 

Replacement

Ballast

EL4 92.3 32.5 W T8 & 0.75 BF Elec 18.40 92.9 7.1 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 20.22 94.2 5.8 EL4 93.0 26.6 W T8 & 0.88 BF Elec 29.24 97.3 2.7 EL5 95.4 32.5 W T8 & 0.71 BF Elec 22.09 95.4 4.6 EL5 96.0 28.4 W T8 & 0.78 BF Elec 26.18 97.2 2.8 

Baseline Baseline 77.9 34 W T12 & 0.88 BF Mag N/A N/A N/A 

EL1 82.4 34 W T12 & 0.88 BF Elec ­16.94 5.3 94.7 

EL2 85.3 34 W T12 & 0.86 BF Elec ­22.02 2.4 97.6 

EL2 86.2 32.5 W T8 & 0.88 BF Elec ­3.29 33.4 66.6 

Event II: EL3 90.8 32.5 W T8 & 0.78 BF Elec 6.30 61.8 38.2 

Standards Lamp & Ballast EL3 91.2 34 W T12 & 0.86 BF Elec ­22.29 2.7 97.3 

Induced Retrofit Replacement EL4 92.3 32.5 W T8 & 0.75 BF Elec 11.49 75.6 24.4 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 13.31 78.5 21.5 EL4 93.0 26.6 W T8 & 0.88 BF Elec 22.33 92.2 7.8 EL5 95.4 32.5 W T8 & 0.71 BF Elec 15.18 83.6 16.4 EL5 96.0 28.4 W T8 & 0.78 BF Elec 19.27 89.2 10.8 

8B­9

EE-2006-STD-0131 COMMENT 37.2
Table 8B.2 LCC and PBP Monte Carlo Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin System 

Commercial Sector (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 77.9 34 W T12 & 0.88 BF Elec N/A N/A N/A 

EL1 82.4 34 W T12 & 0.86 BF Elec ­1.74 0.1 99.9 

EL2 85.3 34 W T12 & 0.86 BF Elec ­8.77 0.0 100.0 

EL2 86.2 32.5 W T8 & 0.88 BF Elec 9.95 100.0 0.0 

Event III: Ballast

Failure Lamp & Ballast

EL3 90.8 32.5 W T8 & 0.78 BF Elec 19.54 100.0 0.0 

EL3 91.2 34 W T12 & 0.86 BF Elec ­9.05 0.0 100.0 

Replacement EL4 92.3 32.5 W T8 & 0.75 BF Elec 24.74 100.0 0.0 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 26.56 100.0 0.0 EL4 93.0 26.6 W T8 & 0.88 BF Elec 35.57 100.0 0.0 EL5 95.4 32.5 W T8 & 0.71 BF Elec 28.43 100.0 0.0 EL5 96.0 28.4 W T8 & 0.78 BF Elec 32.52 100.0 0.0 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec N/A N/A N/A 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 18.22 100.0 0.0 

Event IV: Ballast

Retrofit Lamp & Ballast

Replacement

EL4 92.3 32.5 W T8 & 0.75 BF Elec 23.41 100.0 0.0 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 25.23 100.0 0.0 EL4 93.0 26.6 W T8 & 0.88 BF Elec 34.25 100.0 0.0 EL5 95.4 32.5 W T8 & 0.71 BF Elec 27.10 100.0 0.0 EL5 96.0 28.4 W T8 & 0.78 BF Elec 31.19 100.0 0.0 

8B­10

EE-2006-STD-0131 COMMENT 37.2
Table 8B.3 LCC and PBP Monte Carlo Results for a Three­Lamp 4­foot 32W T8 Medium Bipin System O

Commercial Sector

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec N/A N/A N/A 

Event I: Lamp EL4 93.8 30.4 W T8 & 0.88 BF Elec 4.61 99.9 0.1 

Failure A: Lamp

Replacement EL4 93.0 26.6 W T8 & 0.88 BF Elec 25.03 100.0 0.0 

EL5 96.0 28.4 W T8 & 0.88 BF Elec 11.19 100.0 0.0 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec N/A N/A N/A 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 9.36 100.0 0.0 

Event III: Ballast

Failure Lamp & Ballast

EL4 92.3 32.5 W T8 & 0.75 BF Elec 14.46 100.0 0.0 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 16.22 100.0 0.0 

Replacement EL4 93.0 26.6 W T8 & 0.88 BF Elec 25.03 100.0 0.0 

EL5 95.4 32.5 W T8 & 0.75 BF Elec 13.07 100.0 0.0 EL5 96.0 28.4 W T8 & 0.88 BF Elec 11.19 100.0 0.0 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec N/A N/A N/A 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 9.36 100.0 0.0 

Event V: New EL4 92.3 32.5 W T8 & 0.75 BF Elec 14.46 100.0 0.0 

Construction and New Lamp & EL4 93.8 30.4 W T8 & 0.78 BF Elec 16.22 100.0 0.0 

Renovation Ballast Purchase EL4 93.0 26.6 W T8 & 0.88 BF Elec 25.03 100.0 0.0 

EL5 95.4 32.5 W T8 & 0.75 BF Elec 13.07 100.0 0.0 EL5 96.0 28.4 W T8 & 0.88 BF Elec 11.19 100.0 0.0 

For the 4­foot medium bipin product class with CCT less than or equal to 4,500K in the residential sector

baseline lamp: a 40W T12. The lamp was analyzed at five efficacy levels with minimum efficacy requirements 

94 lm/W. The following tables present the LCC savings and PBP Monte Carlo results for this 4­foot medium bip

in the residential sector. Key inputs consist of using the AEO2008 reference case electricity prices, and medium­

ballast prices. For the lamp failure event, residential high operating hours were used. For other events, residenti

hours were used.

8B­11

EE-2006-STD-0131 COMMENT 37.2
Table 8B.4 LCC and PBP Monte Carlo Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin System O

Residential Sector Using Average Operating Hours

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 76.8 41 W T12 & 0.68 BF Mag N/A N/A N/A 

EL1 80.5 41 W T12 & 0.65 BF Elec 9.78 100.00 0.00 

EL1 82.4 34 W T12 & 0.85 BF Elec 9.79 100.00 0.00 EL1 82.9 41 W T12 & 0.65 BF Elec 6.69 98.50 1.50 EL2 85.3 34 W T12 & 0.75 BF Elec 18.30 100.00 0.00 EL2 86.2 32.5 W T8 & 0.78 BF Elec 18.13 100.00 0.00 

Event III: Ballast

Failure Lamp & Ballast

EL2 87.8 41 W T12 & 0.65 BF Elec 6.49 96.90 3.10 

EL3 91.2 34 W T12 & 0.66 BF Mag 0.96 54.10 45.90 

Replacement EL3 91.2 34 W T12 & 0.75 BF Elec 16.18 100.00 0.00 

EL3 90.8 32.5 W T8 & 0.75 BF Elec 18.02 100.00 0.00 EL4 92.3 32.5 W T8 & 0.75 BF Elec 17.74 100.00 0.00 EL4 93.8 30.4 W T8 & 0.75 BF Elec 19.40 100.00 0.00 EL4 93.0 26.6 W T8 & 0.78 BF Elec 23.24 100.00 0.00 

EL5 95.4 32.5 W T8 & 0.71 BF Elec 19.30 100.00 0.00 

EL5 96.0 28.4 W T8 & 0.78 BF Elec 21.32 100.00 0.00 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec N/A N/A N/A 

EL3 91.2 34 W T12 & 0.75 BF Elec 4.55 89.30 10.70 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 4.44 100.00 0.00 

Event V: New

Construction and

Renovation

New Lamp &

Ballast Purchase

EL4 92.3 32.5 W T8 & 0.78 BF Elec 4.16 100.00 0.00 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 6.17 100.00 0.00 EL4 93.0 26.6 W T8 & 0.88 BF Elec 6.98 96.10 3.90 EL5 95.4 32.5 W T8 & 0.75 BF Elec 5.07 98.60 1.40 EL5 96.0 28.4 W T8 & 0.78 BF Elec 9.69 100.00 0.00 

8B­12

EE-2006-STD-0131 COMMENT 37.2
Table 8B.5 LCC and PBP Monte Carlo Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin System O

Residential Sector Using High Operating Hours

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 76.8 41 W T12 & 0.68 BF Mag N/A N/A N/A 

A: Lamp

Replacement EL3 91.2 34 W T12 & 0.66 BF Mag ­6.44 0.00 100.00 

EL1 80.5 41 W T12 & 0.65 BF Elec ­8.18 0.00 100.00 EL1 82.4 34 W T12 & 0.85 BF Elec ­7.91 0.00 100.00 EL1 82.9 41 W T12 & 0.65 BF Elec ­9.07 0.00 100.00 EL2 85.3 34 W T12 & 0.75 BF Elec ­6.40 6.60 93.40 EL2 86.2 32.5 W T8 & 0.78 BF Elec ­6.21 5.30 94.70 

Event I: Lamp

Failure B: Lamp &

Ballast

Replacement

EL2 87.8 41 W T12 & 0.65 BF Elec ­9.12 0.00 100.00 

EL3 91.2 34 W T12 & 0.66 BF Mag ­10.58 0.00 100.00 EL3 91.2 34 W T12 & 0.75 BF Elec ­7.01 5.30 94.70 EL3 90.8 32.5 W T8 & 0.75 BF Elec ­6.38 5.80 94.20 EL4 92.3 32.5 W T8 & 0.75 BF Elec ­6.46 5.70 94.30 EL4 93.8 30.4 W T8 & 0.75 BF Elec ­6.14 7.20 92.80 EL4 93.0 26.6 W T8 & 0.78 BF Elec ­5.48 14.50 85.50 EL5 95.4 32.5 W T8 & 0.71 BF Elec ­6.19 7.20 92.80 EL5 96.0 28.4 W T8 & 0.78 BF Elec ­5.69 9.80 90.20 

8B.7.1.2 Product Class: 4­foot T5 miniature bipin high output ≤ 4,500K

For the 4­foot T5 miniature bipin high output product class with CCT less than or equal to 4,500K in the 

DOE analyzed one baseline lamp: a 54W T5. Other key inputs consist of using AEO2008 reference case electric

medium­range lamp and ballast prices. DOE analyzes multiple lamp substitutions with each lamp substitution co

efficacy requirements of 89 lm/W. The following table presents the LCC savings and PBP Monte Carlo results f

8B­13

EE-2006-STD-0131 COMMENT 37.2
Table 8B.6 LCC and PBP Monte Carlo Results for a Two­Lamp 4­Foot 54W T5 Miniature Bipin High Ou

Operating in the Industrial Sector

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Event I: Lamp

Failure

Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec N/A N/A N/A 

A: Lamp

Replacement EL1 98.0 51 W T5 & 1 BF Elec ­3.91 0.00 100.00 

Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec N/A N/A N/A 

Event III: Ballast

Failure Lamp and Ballast

Replacement

EL1 98.0 51 W T5 & 1 BF Elec ­3.91 0.00 100.00 

Event V: New Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec N/A N/A N/A 

Construction and New Lamp & EL1 92.9 53.8 W T5 & 1 BF Elec 50.01 100.00 0.00 

Renovation Ballast Purchase EL1 98.0 51 W T5 & 1 BF Elec 50.70 100.00 0.00 

8B.7.1.3 Product Class: 4­foot T5 miniature bipin standard output ≤ 4,500K

For the 4­foot T5 miniature bipin standard output product class with CCT less than or equal to 4,500K in 

sector, DOE analyzed one baseline lamp: a 28W T5. Other key inputs consist of using AEO2008 reference case 

medium­range lamp and ballast prices. DOE analyzes multiple lamp substitutions with each lamp substitution co

efficacy requirements of 103 and 108 lm/W. The LCC savings and PBP Monte Carlo results for this product cla

table below.

8B­14

EE-2006-STD-0131 COMMENT 37.2
Table 8B.7 LCC and PBP Monte Carlo Results for a Two­Lamp 4­Foot 28W T5 Miniature Bipin Standard 

Operating in the Commercial Sector

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Event I: Lamp

Failure

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec N/A N/A N/A 

A: Lamp

Replacement EL2 111.5 26 W T5 & 1.15 BF Elec 1.17 80.20 19.80 

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec N/A N/A N/A 

Event III: Ballast EL1 104.3 27.8 W T5 & 0.95 BF Elec 9.56 100.00 0.00 

Failure Lamp & Ballast

Replacement EL2 109.7 27.8 W T5 & 0.9 BF Elec 10.70 100.00 0.00 

EL2 111.5 26 W T5 & 0.9 BF Elec 19.62 100.00 0.00 

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec N/A N/A N/A 

Event V: New

Construction and

Renovation

New Lamp &

Ballast Purchase

EL1 104.3 27.8 W T5 & 0.95 BF Elec 41.48 100.00 0.00 

EL2 109.7 27.8 W T5 & 0.9 BF Elec 45.50 100.00 0.00 EL2 111.5 26 W T5 & 0.9 BF Elec 43.90 100.00 0.00 

8B.7.1.4 Product Class: 8­foot single pin slimline ≤ 4,500K

For the 8­foot single­pin slimline product class with CCT less than or equal to 4,500K in the commercial 

three baseline lamps: a 75W T12, 60W T12, and 59W T8. Each lamp was analyzed at five efficacy levels with m

requirements of 89, 93, 95, 97, and 100 lm/W. The following tables present the LCC savings and PBP Monte Ca

three 8­foot single pin slimline baselines operating in the commercial sector. Key inputs consist of using the AE

electricity prices, and medium­range lamp and ballast prices. Note: Lamp replacement results in Event I are not 

lamp because there are no energy saving lamp replacement options.

8B­15

EE-2006-STD-0131 COMMENT 37.2
Table 8B.8 LCC and PBP Monte Carlo Results for a Two­Lamp 8­Foot 75W T12 Single Pin Slimline Syst

Commercial Sector

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 85.6 75 W T12 & 0.94 BF Mag N/A N/A N/A 

A: Lamp

Replacement EL3 97.5 60.5 W T12 & 0.88 BF Mag 35.26 100.0 0.0 

Event I: Lamp

Failure B: Lamp &

EL1 87.3 75 W T12 & 0.85 BF Elec ­12.89 12.5 87.5 

EL2 92.0 75 W T12 & 0.85 BF Elec ­9.24 18.2 81.8 

Ballast

Replacement EL3 94.8 60.1 W T8 & 1.18 BF Elec ­27.95 0.0 100.0 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 18.91 91.8 8.2 

Baseline Baseline 85.6 75 W T12 & 0.94 BF Mag N/A N/A N/A 

Event II: EL1 87.3 75 W T12 & 0.85 BF Elec ­22.46 3.1 96.9 

Standards Lamp & Ballast EL2 92.0 75 W T12 & 0.85 BF Elec ­18.81 6.4 93.6 

Induced Retrofit Replacement EL3 94.8 60.1 W T8 & 1.18 BF Elec ­37.52 0.0 100.0 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 9.34 68.3 31.7 

Baseline Baseline 85.6 75 W T12 & 0.88 BF Elec N/A N/A N/A 

Event III: Ballast EL1 87.3 75 W T12 & 0.85 BF Elec ­4.67 0.0 100.0 

Failure Lamp & Ballast

Replacement EL2 92.0 75 W T12 & 0.85 BF Elec ­1.03 16.0 84.0 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 27.13 100.0 0.0 

Event IV: Ballast

Retrofit

Baseline Baseline/EL3 94.8 60.1 W T8 & 1.18 BF Elec N/A N/A N/A 

Lamp & Ballast

Replacement EL5 101.5 60.1 W T8 & 0.88 BF Elec 46.86 100.0 0.0 

8B­16

EE-2006-STD-0131 COMMENT 37.2
Table 8B.9 LCC and PBP Monte Carlo Results for a Two­Lamp 8­Foot 60W T12 Single Pin Slimline Syst

Commercial Sector

Event Response Efficacy Level

Rated

Lamp

Efficacy

Design Option

Average

LCC

Savings

Net Benefit Net Cost M

lms/W $ % % 

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Mag N/A N/A N/A 

EL2 92.6 60.5 W T12 & 0.85 BF Elec ­18.03 2.8 97.2 

Event I: Lamp

Failure B: Lamp &

EL3 97.5 60.5 W T12 & 0.85 BF Elec ­17.47 3.2 96.8 

Ballast EL3 94.8 60.1 W T8 & 0.88 BF Elec ­17.67 1.0 99.0 

Replacement

EL4 98.2 60.1 W T8 & 0.78 BF Elec ­8.55 20.5 79.5 

EL5 101.8 57 W T8 & 0.78 BF Elec ­6.09 27.6 72.4 EL5 101.5 60.1 W T8 & 0.78 BF Elec ­7.86 23.1 76.9 

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Mag N/A N/A N/A 

EL2 92.6 60.5 W T12 & 0.85 BF Elec ­25.11 0.4 99.6 

Event II:

Standards

Induced Retrofit Lamp & Ballast

Replacement

EL3 97.5 60.5 W T12 & 0.85 BF Elec ­24.55 0.5 99.5 

EL3 94.8 60.1 W T8 & 0.88 BF Elec ­24.74 0.0 100.0 EL4 98.2 60.1 W T8 & 0.78 BF Elec ­15.63 8.5 91.5 

EL5 101.8 57 W T8 & 0.78 BF Elec ­13.16 11.0 89.0 

EL5 101.5 60.1 W T8 & 0.78 BF Elec ­14.93 9.4 90.6 

8B­17

EE-2006-STD-0131 COMMENT 37.2
Table 8B.9 LCC and PBP Monte Carlo Results for a Two­Lamp 8­Foot 60W T12 Single Pin Slimline Syst

Commercial Sector (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

Design Option

Average

LCC

Savings

Net Benefit Net Cost M

lms/W $ % % 

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Elec N/A N/A N/A 

EL2 92.6 60.5 W T12 & 0.85 BF Elec ­2.54 0.3 99.7 

Event III: Ballast

Failure Lamp & Ballast EL3 97.5 60.5 W T12 & 0.85 BF Elec ­1.98 4.6 95.4 

Replacement EL4 98.2 60.1 W T8 & 0.78 BF Elec 6.94 100.0 0.0 

EL5 101.8 57 W T8 & 0.78 BF Elec 9.40 100.0 0.0 EL5 101.5 60.1 W T8 & 0.78 BF Elec 7.63 100.0 0.0 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec N/A N/A N/A 

Event IV: Ballast EL4 98.2 60.1 W T8 & 0.78 BF Elec 9.12 100.0 0.0 

Retrofit Lamp & Ballast

Replacement EL5 101.8 57 W T8 & 0.78 BF Elec 11.58 100.0 0.0 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 9.81 100.0 0.0 

8B­18

EE-2006-STD-0131 COMMENT 37.2
Table 8B.10 LCC and PBP Monte Carlo Results for a Two­Lamp 8­Foot 59W T8 Single Pin Slimline Syst

Commercial Sector

Event Response Candidate Standard Level Rated Lamp Efficacy

lms/W

Design Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Event I: Lamp

Failure

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec N/A N/A N/A 

A: Lamp EL5 101.8 57 W T8 & 0.88 BF Elec 6.08 100.0 0.0 

Replacement EL5 103.6 55 W T8 & 0.88 BF Elec 9.93 100.0 0.0 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec N/A N/A N/A 

Event III: Ballast

Failure Lamp & Ballast

EL4 98.2 60.1 W T8 & 0.85 BF Elec ­0.34 29.7 70.3 

EL5 101.8 57 W T8 & 0.85 BF Elec 7.71 100.0 0.0 

Replacement EL5 101.5 60.1 W T8 & 0.78 BF Elec 9.76 100.0 0.0 

EL5 103.6 55 W T8 & 0.88 BF Elec 9.93 100.0 0.0 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec N/A N/A N/A 

Event V: New EL4 98.2 60.1 W T8 & 0.85 BF Elec ­0.34 29.7 70.3 

Construction and New Lamp & EL5 101.8 57 W T8 & 0.85 BF Elec 7.71 100.0 0.0 

Renovation Ballast Purchase EL5 101.5 60.1 W T8 & 0.78 BF Elec 9.76 100.0 0.0 

EL5 103.6 55 W T8 & 0.88 BF Elec 9.93 100.0 0.0 

8B.7.1.5 Product Class: 8­foot recessed double contact high output ≤ 4,500KFor the 8­foot recessed double contact HO operating in the industrial sector with CCT less than or equal t

analyzed two baseline lamps: a 110W T12 and 95W T12. Each lamp was analyzed at five efficacy levels with m

requirements of 83, 87, 88, 92, and 95 lm/W. The following tables present the LCC savings and PBP Monte Carl

the 8­foot recessed double contact high output baselines operating in the industrial sector. Key inputs consist of 

reference case electricity prices, and medium­range lamp and ballast prices. Note: Lamp replacement results in E

for a 95W T12 lamp because there are no energy saving lamp replacement options.

8B­19

EE-2006-STD-0131 COMMENT 37.2
Table 8B.11 LCC and PBP Monte Carlo Results for a Two­Lamp 8­Foot 110W T12 Recessed Double Con

Operating in the Industrial Sector

Event Response Efficacy Level

Rated

Lamp

Efficacy

Design Option

Average

LCC

Savings

Net Benefit Net Cost M

lms/W $ % % 

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag N/A N/A N/A 

A: Lamp EL3 87.6 97 W T12 & 0.91 BF Mag 5.13 100.0 0.0 

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 4.51 99.6 0.4 

Event I: Lamp EL1 83.2 113 W T12 & 0.88 BF Elec ­23.84 0.0 100.0 

Failure

B: Lamp & EL3 87.6 97 W T12 & 0.91 BF Mag ­22.27 0.0 100.0 

Ballast EL3 88.9 97 W T12 & 0.91 BF Mag ­22.89 0.0 100.0 

Replacement EL3 88.9 97 W T12 & 0.9 BF Elec ­15.28 3.6 96.4 

EL5 95.3 86 W T8 & 0.88 BF Elec 7.73 80.6 19.4 

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag N/A N/A N/A 

EL1 83.2 113 W T12 & 0.88 BF Elec ­34.17 0.0 100.0 

Event II:

Standards

Induced Retrofit

Lamp & Ballast

Replacement

EL3 87.6 97 W T12 & 0.91 BF Mag ­32.60 0.0 100.0 

EL3 88.9 97 W T12 & 0.91 BF Mag ­33.22 0.0 100.0 

EL3 88.9 97 W T12 & 0.9 BF Elec ­25.61 0.0 100.0 

EL5 95.3 86 W T8 & 0.88 BF Elec ­2.60 33.3 66.7 

8B­20

EE-2006-STD-0131 COMMENT 37.2
Table 8B.11 LCC and PBP Monte Carlo Results for a Two­Lamp 8­Foot 110W T12 Recessed Double Con

Operating in the Industrial Sector (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

Design Option

Average

LCC

Savings

Net Benefit Net Cost M

lms/W $ % % 

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag N/A N/A N/A 

EL1 83.2 113 W T12 & 0.88 BF Elec 3.56 97.2 2.8 

Event III: Ballast EL3 87.6 97 W T12 & 0.91 BF Mag 5.13 100.0 0.0 

Failure Lamp & Ballast

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 4.51 99.6 0.4 

EL3 88.9 97 W T12 & 0.9 BF Elec 12.12 100.0 0.0 EL5 95.3 86 W T8 & 0.88 BF Elec 35.13 100.0 0.0 

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag N/A N/A N/A 

EL1 83.2 113 W T12 & 0.88 BF Elec 3.56 97.2 2.8 

EL2 86.1 97 W T12 & 0.9 BF Elec 3.87 97.7 2.3 

EL2 86.1 97 W T12 & 0.91 BF Mag ­2.90 0.5 99.5 

Event V: New EL3 87.6 97 W T12 & 0.9 BF Elec ­6.96 5.4 94.6 

Construction and New Lamp & EL3 87.6 97 W T12 & 0.91 BF Mag 5.13 100.0 0.0 

Renovation Ballast Purchase EL3 88.9 97 W T12 & 0.9 BF Elec 12.12 100.0 0.0 

EL3 88.9 97 W T12 & 0.91 BF Mag 4.51 99.6 0.4 EL4 91.9 86 W T8 & 0.88 BF Elec 8.99 97.3 2.7 

EL4 93.0 86 W T8 & 0.81 BF Elec ­0.56 43.5 56.5 EL5 95.3 86 W T8 & 0.81 BF Elec 10.16 97.6 2.4 

8B­21

EE-2006-STD-0131 COMMENT 37.2
Table 8B.12 LCC and PBP Monte Carlo Results for a Two­Lamp 8­Foot 95W T12 Recessed Double Cont

Operating in the Industrial Sector

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag N/A N/A N/A 

EL2 86.1 97 W T12 & 0.89 BF Elec ­23.59 0.0 100.0 

Event I: Lamp

Failure

B: Lamp &

EL3 87.6 97 W T12 & 0.88 BF Elec ­33.61 0.0 100.0 

EL3 88.9 97 W T12 & 0.88 BF Elec ­34.23 0.0 100.0 

Replacement

Ballast

EL4 91.9 86 W T8 & 0.88 BF Elec ­10.50 8.7 91.3 

EL4 93.0 86 W T8 & 0.88 BF Elec ­13.64 3.5 96.5 EL5 95.3 86 W T8 & 0.81 BF Elec ­11.02 9.3 90.7 

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag N/A N/A N/A 

EL2 86.1 97 W T12 & 0.89 BF Elec ­31.18 0.0 100.0 

Event II: EL3 87.6 97 W T12 & 0.88 BF Elec ­41.19 0.0 100.0 

Standards Lamp & Ballast EL3 88.9 97 W T12 & 0.88 BF Elec ­41.82 0.0 100.0 

Induced Retrofit Replacement EL4 91.9 86 W T8 & 0.88 BF Elec ­18.09 1.6 98.4 

EL4 93.0 86 W T8 & 0.88 BF Elec ­21.22 0.0 100.0 EL5 95.3 86 W T8 & 0.81 BF Elec ­18.61 2.1 97.9 

8B­22

EE-2006-STD-0131 COMMENT 37.2
Table 8B.12 LCC and PBP Monte Carlo Results for a Two­Lamp 8­Foot 95W T12 Recessed Double Cont

Operating in the Industrial Sector (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag N/A N/A N/A 

EL2 86.1 97 W T12 & 0.89 BF Elec 3.76 100.0 0.0 

Event III: Ballast

Failure Lamp & Ballast

EL3 87.6 97 W T12 & 0.88 BF Elec ­6.26 6.2 93.8 

EL3 88.9 97 W T12 & 0.88 BF Elec ­6.88 5.5 94.5 

Replacement EL4 91.9 86 W T8 & 0.88 BF Elec 16.85 100.0 0.0 

EL4 93.0 86 W T8 & 0.88 BF Elec 13.72 100.0 0.0 

EL5 95.3 86 W T8 & 0.81 BF Elec 16.33 100.0 0.0 

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag N/A N/A N/A 

EL2 86.1 97 W T12 & 0.89 BF Elec 3.76 100.0 0.0 

Event V: New EL3 87.6 97 W T12 & 0.88 BF Elec ­6.26 6.2 93.8 

Construction and New Lamp & EL3 88.9 97 W T12 & 0.88 BF Elec ­6.88 5.5 94.5 

Renovation Ballast Purchase EL4 91.9 86 W T8 & 0.88 BF Elec 16.85 100.0 0.0 

EL4 93.0 86 W T8 & 0.88 BF Elec 13.72 100.0 0.0 

EL5 95.3 86 W T8 & 0.81 BF Elec 16.33 100.0 0.0 

8B­23

EE-2006-STD-0131 COMMENT 37.2
8B.7.2 Lamp and Ballast Price Scenario Results

As mentioned earlier, DOE also analyzed LCC savings and PBP results using a scenario

analysis. Specifically, because the LCC and PBP results are highly dependent on equipment

prices, DOE examined several sensitivities to the medium lamp price and ballast price results

presented in Chapter 8. Chapter 7 described three prices (low, medium, and high) DOE

developed for each general service fluorescent lamp. The following tables present LCC savings

and PBP results using the low and high lamp prices. In addition, because DOE analyzes GSFL

by considering both the lamp and the ballast, results presented in Chapter 7 account for the first

cost of the ballast. However, as a sensitivity to the analysis, DOE presents LCC and PBP results

assuming that the ballast price is equal to zero.

8B.7.2.1 Product Class: 4­foot medium bipin ≤ 4,500K

The following tables present the findings of an LCC analysis on the three 4­foot medium bipin

GSFL baselines operating in the commercial sector with a CCT less than or equal to 4,500K,

considering low lamp prices, high lamp prices, or no ballast prices. Key inputs consist of using

AEO2008 reference case electricity prices and an analysis period of 5.5 yrs. Note: Lamp

replacement results in Event I are not shown for a 34W T12 lamp because there are no energy

saving lamp replacement options.

8B­24

EE-2006-STD-0131 COMMENT 37.2
Table 8B.13 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector with High Lamp Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operati

Cost Sav

(Start Ye

$

Baseline Baseline 78.0 41 W T12 & 0.95 BF Mag 205.21 0.00 16.97 0.00 

A: Lamp

Replacement EL3 91.2 34 W T12 & 0.88 BF Mag 186.57 18.64 32.60 7.08 

EL1 80.5 41 W T12 & 0.88 BF Elec 214.11 ­8.90 78.17 7.20 

EL1 82.9 41 W T12 & 0.87 BF Elec 215.86 ­10.64 84.67 7.43 

EL2 86.2 32.5 W T8 & 1.18 BF Elec 211.02 ­5.80 67.32 5.29 

Event I: EL2 87.8 41 W T12 & 0.87 BF Elec 216.23 ­11.01 85.08 7.43 

Lamp Failure B: Lamp &

Ballast

Replacement

EL3 91.2 34 W T12 & 0.88 BF Elec 193.48 11.74 84.53 12.60 

EL3 90.8 32.5 W T8 & 1 BF Elec 192.22 13.00 71.66 10.66 

EL4 92.3 32.5 W T8 & 0.88 BF Elec 170.59 34.62 64.58 14.24 

EL4 93.8 30.4 W T8 & 1 BF Elec 183.68 21.53 73.45 13.06 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 179.36 25.85 78.72 13.92 

EL5 95.4 32.5 W T8 & 0.88 BF Elec 172.53 32.68 66.77 14.24 EL5 96.0 28.4 W T8 & 1 BF Elec 177.37 27.84 72.61 15.18 

8B­25

EE-2006-STD-0131 COMMENT 37.2
Table 8B.13 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector with High Lamp Prices (continued)

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline 78.0 41 W T12 & 0.95 BF Mag 197.01 0.00 16.97 0.00 

EL1 80.5 41 W T12 & 0.88 BF Elec 215.47 ­18.46 80.48 7.20 

EL1 82.9 41 W T12 & 0.87 BF Elec 217.22 ­20.21 86.98 7.43 EL2 86.2 32.5 W T8 & 1.18 BF Elec 212.38 ­15.37 69.63 5.29 

Event II:

Standards Lamp &

EL2 87.8 41 W T12 & 0.87 BF Elec 217.59 ­20.58 87.39 7.43 

EL3 91.2 34 W T12 & 0.88 BF Elec 194.84 2.17 86.84 12.60 

Induced

Retrofit

Ballast

Replacement

EL3 90.8 32.5 W T8 & 1 BF Elec 193.58 3.43 73.97 10.66 

EL4 92.3 32.5 W T8 & 0.88 BF Elec 171.95 25.06 66.89 14.24 

EL4 93.8 30.4 W T8 & 1 BF Elec 185.05 11.96 75.76 13.06 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 180.73 16.28 81.03 13.92 

EL5 95.4 32.5 W T8 & 0.88 BF Elec 173.90 23.11 69.08 14.24 

EL5 96.0 28.4 W T8 & 1 BF Elec 178.73 18.28 74.92 15.18 

Baseline Baseline 78.0 41 W T12 & 0.88 BF Elec 204.85 0.00 68.90 0.00 

EL1 80.5 41 W T12 & 0.87 BF Elec 213.12 ­8.28 78.17 0.23 

EL1 82.9 41 W T12 & 0.87 BF Elec 215.86 ­11.01 84.67 0.23 

EL2 87.8 41 W T12 & 0.87 BF Elec 216.23 ­11.38 85.08 0.23 

Event III: EL3 91.2 34 W T12 & 0.88 BF Elec 193.48 11.37 84.53 5.40 

Ballast Lamp & EL3 90.8 32.5 W T8 & 1 BF Elec 192.22 12.63 71.66 3.46 

Failure Ballast

Replacement EL4 92.3 32.5 W T8 & 0.88 BF Elec 170.59 34.26 64.58 7.04 

EL4 93.8 30.4 W T8 & 1 BF Elec 183.68 21.16 73.45 5.85 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 179.36 25.48 78.72 6.72 

EL5 95.4 32.5 W T8 & 0.88 BF Elec 172.53 32.31 66.77 7.04 

EL5 96.0 28.4 W T8 & 1 BF Elec 177.37 27.48 72.61 7.98 

* Comparative lumens are sometimes non­zero for baseline T12 electronic systems under events III and IV (ballast failure and retro

package is compared to a system with a T12 magnetic ballast. DOE chose to compare these systems for these events because it recog

regulations will prohibit the use of magnetic ballasts, future purchasers may still seek the current lumen package delivered by curren

8B­26

EE-2006-STD-0131 COMMENT 37.2
Table 8B.13 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector with High Lamp Prices (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL2 86.2 32.5 W T8 & 1.18 BF Elec 212.38 0.00 69.63 

EL3 91.2 34 W T12 & 0.88 BF Elec 194.84 17.54 86.84 

EL3 90.8 32.5 W T8 & 1 BF Elec 193.58 18.80 73.97 

Event IV: EL4 92.3 32.5 W T8 & 0.88 BF Elec 171.95 40.43 66.89 

Ballast Retrofit Lamp & Ballast

Replacement EL4 93.8 30.4 W T8 & 1 BF Elec 185.05 27.33 75.76 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 180.73 31.65 81.03 EL5 95.4 32.5 W T8 & 0.88 BF Elec 173.90 38.48 69.08 EL5 96.0 28.4 W T8 & 1 BF Elec 178.73 33.65 74.92 

8B­27

EE-2006-STD-0131 COMMENT 37.2
Table 8B.14 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector with Low Lamp Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operati

Cost Sav

(Start Ye

$

Baseline Baseline 78.0 41 W T12 & 0.95 BF Mag 199.19 0.00 10.95 0.00 

A: Lamp

Replacement EL3 91.2 34 W T12 & 0.88 BF Mag 173.29 25.91 17.65 7.08 

EL1 80.5 41 W T12 & 0.88 BF Elec 202.80 ­3.61 66.86 7.20 

EL1 82.9 41 W T12 & 0.87 BF Elec 202.50 ­3.31 69.64 7.43 EL2 86.2 32.5 W T8 & 1.18 BF Elec 206.60 ­7.40 62.90 5.29 

Event I: EL2 87.8 41 W T12 & 0.87 BF Elec 202.66 ­3.46 69.82 7.43 

Lamp Failure B: Lamp &

Ballast

Replacement

EL3 91.2 34 W T12 & 0.88 BF Elec 180.19 19.01 69.58 12.60 

EL3 90.8 32.5 W T8 & 1 BF Elec 185.31 13.88 64.76 10.66 

EL4 92.3 32.5 W T8 & 0.88 BF Elec 164.15 35.04 57.33 14.24 

EL4 93.8 30.4 W T8 & 1 BF Elec 175.76 23.43 65.53 13.06 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 170.83 28.37 67.78 13.92 

EL5 95.4 32.5 W T8 & 0.88 BF Elec 164.98 34.21 58.27 14.24 EL5 96.0 28.4 W T8 & 1 BF Elec 168.60 30.59 65.16 15.18 

8B­28

EE-2006-STD-0131 COMMENT 37.2
Table 8B.14 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector with Low Lamp Prices (continued)

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline 78.0 41 W T12 & 0.95 BF Mag 193.76 0.00 10.95 0.00 

EL1 80.5 41 W T12 & 0.88 BF Elec 204.16 ­10.40 69.16 7.20 

EL1 82.9 41 W T12 & 0.87 BF Elec 203.86 ­10.10 71.95 7.43 EL2 86.2 32.5 W T8 & 1.18 BF Elec 207.96 ­14.20 65.21 5.29 

Event II:

Standards Lamp &

EL2 87.8 41 W T12 & 0.87 BF Elec 204.02 ­10.26 72.13 7.43 

EL3 91.2 34 W T12 & 0.88 BF Elec 181.55 12.21 71.89 12.60 

Induced

Retrofit

Ballast

Replacement

EL3 90.8 32.5 W T8 & 1 BF Elec 186.67 7.08 67.07 10.66 

EL4 92.3 32.5 W T8 & 0.88 BF Elec 165.51 28.25 59.64 14.24 

EL4 93.8 30.4 W T8 & 1 BF Elec 177.12 16.64 67.83 13.06 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 172.19 21.57 70.09 13.92 

EL5 95.4 32.5 W T8 & 0.88 BF Elec 166.35 27.41 60.58 14.24 

EL5 96.0 28.4 W T8 & 1 BF Elec 169.96 23.79 67.47 15.18 

Baseline Baseline 78.0 41 W T12 & 0.88 BF Elec 198.83 0.00 62.89 0.00 

EL1 80.5 41 W T12 & 0.87 BF Elec 201.81 ­2.98 66.86 0.23 

EL1 82.9 41 W T12 & 0.87 BF Elec 202.50 ­3.67 69.64 0.23 EL2 87.8 41 W T12 & 0.87 BF Elec 202.66 ­3.83 69.82 0.23 

Event III: EL3 91.2 34 W T12 & 0.88 BF Elec 180.19 18.64 69.58 5.40 

Ballast Lamp & EL3 90.8 32.5 W T8 & 1 BF Elec 185.31 13.52 64.76 3.46 

Failure Ballast

Replacement EL4 92.3 32.5 W T8 & 0.88 BF Elec 164.15 34.68 57.33 7.04 

EL4 93.8 30.4 W T8 & 1 BF Elec 175.76 23.07 65.53 5.85 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 170.83 28.00 67.78 6.72 

EL5 95.4 32.5 W T8 & 0.88 BF Elec 164.98 33.85 58.27 7.04 

EL5 96.0 28.4 W T8 & 1 BF Elec 168.60 30.23 65.16 7.98 

* Comparative lumens are sometimes non­zero for baseline T12 electronic systems under events III and IV (ballast failure and retrofit) 

package is compared to a system with a T12 magnetic ballast. DOE chose to compare these systems for these events because it recogn

regulations will prohibit the use of magnetic ballasts, future purchasers may still seek the current lumen package delivered by current T

8B­29

EE-2006-STD-0131 COMMENT 37.2
Table 8B.14 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector with Low Lamp Prices (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL2 86.2 32.5 W T8 & 1.18 BF Elec 207.96 0.00 65.21 

EL3 91.2 34 W T12 & 0.88 BF Elec 181.55 26.41 71.89 

EL3 90.8 32.5 W T8 & 1 BF Elec 186.67 21.28 67.07 

Event IV: EL4 92.3 32.5 W T8 & 0.88 BF Elec 165.51 42.45 59.64 

Ballast Retrofit Lamp & Ballast

Replacement EL4 93.8 30.4 W T8 & 1 BF Elec 177.12 30.84 67.83 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 172.19 35.77 70.09 EL5 95.4 32.5 W T8 & 0.88 BF Elec 166.35 41.61 60.58 EL5 96.0 28.4 W T8 & 1 BF Elec 169.96 38.00 67.47 

8B­30

EE-2006-STD-0131 COMMENT 37.2
Table 8B.15 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector with No Ballast Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operati

Cost Sav

(Start Ye

$

Baseline Baseline 78.0 41 W T12 & 0.95 BF Mag 202.20 0.00 13.96 0.00 

A: Lamp

Replacement EL3 91.2 34 W T12 & 0.88 BF Mag 179.93 22.27 25.13 7.08 

EL1 80.5 41 W T12 & 0.88 BF Elec 177.80 24.40 20.58 7.20 

EL1 82.9 41 W T12 & 0.87 BF Elec 178.52 23.68 25.22 7.43 EL2 86.2 32.5 W T8 & 1.18 BF Elec 177.44 24.77 11.97 5.29 

Event I: EL2 87.8 41 W T12 & 0.87 BF Elec 178.79 23.42 25.52 7.43 

Lamp Failure B: Lamp &

Ballast

Replacement

EL3 91.2 34 W T12 & 0.88 BF Elec 156.18 46.03 25.13 12.60 

EL3 90.8 32.5 W T8 & 1 BF Elec 157.39 44.81 15.07 10.66 

EL4 92.3 32.5 W T8 & 0.88 BF Elec 140.53 61.67 15.50 14.24 

EL4 93.8 30.4 W T8 & 1 BF Elec 148.35 53.85 16.35 13.06 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 143.73 58.48 20.11 13.92 

EL5 95.4 32.5 W T8 & 0.88 BF Elec 141.92 60.28 17.06 14.24 EL5 96.0 28.4 W T8 & 1 BF Elec 141.62 60.59 15.74 15.18 

8B­31

EE-2006-STD-0131 COMMENT 37.2
Table 8B.15 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector with No Ballast Prices (continued)

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline 78.0 41 W T12 & 0.95 BF Mag 195.38 0.00 13.96 0.00 

EL1 80.5 41 W T12 & 0.88 BF Elec 177.80 17.58 20.58 7.20 

EL1 82.9 41 W T12 & 0.87 BF Elec 178.52 16.86 25.22 7.43 EL2 86.2 32.5 W T8 & 1.18 BF Elec 177.44 17.95 11.97 5.29 

Event II:

Standards Lamp &

EL2 87.8 41 W T12 & 0.87 BF Elec 178.79 16.60 25.52 7.43 

EL3 91.2 34 W T12 & 0.88 BF Elec 156.18 39.21 25.13 12.60 

Induced

Retrofit

Ballast

Replacement

EL3 90.8 32.5 W T8 & 1 BF Elec 157.39 37.99 15.07 10.66 

EL4 92.3 32.5 W T8 & 0.88 BF Elec 140.53 54.85 15.50 14.24 

EL4 93.8 30.4 W T8 & 1 BF Elec 148.35 47.03 16.35 13.06 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 143.73 51.66 20.11 13.92 

EL5 95.4 32.5 W T8 & 0.88 BF Elec 141.92 53.46 17.06 14.24 

EL5 96.0 28.4 W T8 & 1 BF Elec 141.62 53.77 15.74 15.18 

Baseline Baseline 78.0 41 W T12 & 0.88 BF Elec 171.18 0.00 13.96 0.00 

EL1 80.5 41 W T12 & 0.87 BF Elec 176.81 ­5.63 20.58 0.23 

EL1 82.9 41 W T12 & 0.87 BF Elec 178.52 ­7.34 25.22 0.23 EL2 87.8 41 W T12 & 0.87 BF Elec 178.79 ­7.60 25.52 0.23 

Event III: EL3 91.2 34 W T12 & 0.88 BF Elec 156.18 15.01 25.13 5.40 

Ballast Lamp & EL3 90.8 32.5 W T8 & 1 BF Elec 157.39 13.79 15.07 3.46 

Failure Ballast

Replacement EL4 92.3 32.5 W T8 & 0.88 BF Elec 140.53 30.65 15.50 7.04 

EL4 93.8 30.4 W T8 & 1 BF Elec 148.35 22.83 16.35 5.85 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 143.73 27.46 20.11 6.72 

EL5 95.4 32.5 W T8 & 0.88 BF Elec 141.92 29.26 17.06 7.04 

EL5 96.0 28.4 W T8 & 1 BF Elec 141.62 29.57 15.74 7.98 

* Comparative lumens are sometimes non­zero for baseline T12 electronic systems under events III and IV (ballast failure and retro

package is compared to a system with a T12 magnetic ballast. DOE chose to compare these systems for these events because it recog

regulations will prohibit the use of magnetic ballasts, future purchasers may still seek the current lumen package delivered by curren

8B­32

EE-2006-STD-0131 COMMENT 37.2
Table 8B.15 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector with No Ballast Prices (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL2 86.2 32.5 W T8 & 1.18 BF Elec 177.44 0.00 11.97 

EL3 91.2 34 W T12 & 0.88 BF Elec 156.18 21.26 25.13 

EL3 90.8 32.5 W T8 & 1 BF Elec 157.39 20.04 15.07 

Event IV: EL4 92.3 32.5 W T8 & 0.88 BF Elec 140.53 36.90 15.50 

Ballast Retrofit Lamp & Ballast

Replacement EL4 93.8 30.4 W T8 & 1 BF Elec 148.35 29.08 16.35 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 143.73 33.71 20.11 EL5 95.4 32.5 W T8 & 0.88 BF Elec 141.92 35.51 17.06 EL5 96.0 28.4 W T8 & 1 BF Elec 141.62 35.82 15.74 

8B­33

EE-2006-STD-0131 COMMENT 37.2
Table 8B.16 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin System Operating i

Sector with High Lamp Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline 77.9 34 W T12 & 0.88 BF Mag 170.86 0.00 13.13 0.00 

EL1 82.4 34 W T12 & 0.88 BF Elec 182.92 ­12.07 70.23 5.52 

EL2 85.3 34 W T12 & 0.86 BF Elec 190.79 ­19.93 80.07 5.97 EL2 86.2 32.5 W T8 & 0.88 BF Elec 167.90 2.95 59.64 7.16 

Event I:

Lamp Failure

B: Lamp &

Ballast

Replacement

EL3 90.8 32.5 W T8 & 0.78 BF Elec 159.39 11.47 63.98 10.14 

EL3 91.2 34 W T12 & 0.86 BF Elec 191.50 ­20.64 84.53 5.97 

EL4 92.3 32.5 W T8 & 0.75 BF Elec 153.87 16.99 64.58 11.04 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 152.78 18.08 65.77 12.09 EL4 93.0 26.6 W T8 & 0.88 BF Elec 143.97 26.89 71.04 14.00 EL5 95.4 32.5 W T8 & 0.71 BF Elec 150.67 20.18 66.77 12.23 EL5 96.0 28.4 W T8 & 0.78 BF Elec 148.19 22.67 64.93 13.82 

Baseline Baseline 77.9 34 W T12 & 0.88 BF Mag 164.42 0.00 13.13 0.00 

EL1 82.4 34 W T12 & 0.88 BF Elec 184.29 ­19.87 72.54 5.52 

EL2 85.3 34 W T12 & 0.86 BF Elec 192.15 ­27.73 82.37 5.97 EL2 86.2 32.5 W T8 & 0.88 BF Elec 169.27 ­4.85 61.95 7.16 

Event II:

Standards

Induced

Lamp &

EL3 90.8 32.5 W T8 & 0.78 BF Elec 160.75 3.67 66.29 10.14 

EL3 91.2 34 W T12 & 0.86 BF Elec 192.86 ­28.44 86.84 5.97 

Retrofit

Ballast

Replacement EL4 92.3 32.5 W T8 & 0.75 BF Elec 155.23 9.19 66.89 11.04 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 154.14 10.28 68.08 12.09 

EL4 93.0 26.6 W T8 & 0.88 BF Elec 145.33 19.09 73.34 14.00 EL5 95.4 32.5 W T8 & 0.71 BF Elec 152.04 12.38 69.08 12.23 EL5 96.0 28.4 W T8 & 0.78 BF Elec 149.55 14.87 67.23 13.82 

8B­34

EE-2006-STD-0131 COMMENT 37.2
Table 8B.16 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin System Operating i

Sector with High Lamp Prices (continued)

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operati

Cost Sav

(Start Ye

$

Baseline Baseline 77.9 34 W T12 & 0.88 BF Elec 177.76 0.00 65.06 0.00 

EL1 82.4 34 W T12 & 0.86 BF Elec 180.95 ­3.19 70.23 0.46 

EL2 85.3 34 W T12 & 0.86 BF Elec 190.79 ­13.03 80.07 0.46 

EL2 86.2 32.5 W T8 & 0.88 BF Elec 167.90 9.85 59.64 1.64 

Event III: EL3 90.8 32.5 W T8 & 0.78 BF Elec 159.39 18.37 63.98 4.63 

Ballast Lamp & EL3 91.2 34 W T12 & 0.86 BF Elec 191.50 ­13.74 84.53 0.46 

Failure Ballast

Replacement EL4 92.3 32.5 W T8 & 0.75 BF Elec 153.87 23.89 64.58 5.52 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 152.78 24.98 65.77 6.58 EL4 93.0 26.6 W T8 & 0.88 BF Elec 143.97 33.79 71.04 8.48 EL5 95.4 32.5 W T8 & 0.71 BF Elec 150.67 27.09 66.77 6.72 EL5 96.0 28.4 W T8 & 0.78 BF Elec 148.19 29.57 64.93 8.30 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 169.27 0.00 61.95 0.00 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 160.75 17.01 66.29 4.63 

Event IV: EL4 92.3 32.5 W T8 & 0.75 BF Elec 155.23 22.53 66.89 5.52 

Ballast Lamp & EL4 93.8 30.4 W T8 & 0.78 BF Elec 154.14 23.62 68.08 6.58 

Retrofit Ballast

Replacement EL4 93.0 26.6 W T8 & 0.88 BF Elec 145.33 32.43 73.34 8.48 

EL5 95.4 32.5 W T8 & 0.71 BF Elec 152.04 25.72 69.08 6.72 EL5 96.0 28.4 W T8 & 0.78 BF Elec 149.55 28.21 67.23 8.30 

8B­35

EE-2006-STD-0131 COMMENT 37.2
Table 8B.17 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin System Operating i

Sector with Low Lamp Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline 77.9 34 W T12 & 0.88 BF Mag 167.03 0.00 9.31 0.00 

EL1 82.4 34 W T12 & 0.88 BF Elec 176.15 ­9.11 63.45 5.52 

EL2 85.3 34 W T12 & 0.86 BF Elec 178.39 ­11.36 67.67 5.97 

EL2 86.2 32.5 W T8 & 0.88 BF Elec 163.48 3.55 55.22 7.16 

Event I:

Lamp Failure

B: Lamp &

Ballast

Replacement

EL3 90.8 32.5 W T8 & 0.78 BF Elec 152.49 14.55 57.08 10.14 

EL3 91.2 34 W T12 & 0.86 BF Elec 178.21 ­11.18 69.58 5.97 

EL4 92.3 32.5 W T8 & 0.75 BF Elec 147.43 19.60 57.33 11.04 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 144.85 22.18 57.84 12.09 EL4 93.0 26.6 W T8 & 0.88 BF Elec 135.43 31.60 60.10 14.00 EL5 95.4 32.5 W T8 & 0.71 BF Elec 143.12 23.91 58.27 12.23 EL5 96.0 28.4 W T8 & 0.78 BF Elec 139.42 27.61 57.48 13.82 

Baseline Baseline 77.9 34 W T12 & 0.88 BF Mag 162.36 0.00 9.31 0.00 

EL1 82.4 34 W T12 & 0.88 BF Elec 177.51 ­15.16 65.76 5.52 

EL2 85.3 34 W T12 & 0.86 BF Elec 179.75 ­17.40 69.98 5.97 EL2 86.2 32.5 W T8 & 0.88 BF Elec 164.85 ­2.49 57.52 7.16 

Event II:

Standards

Induced

Lamp &

EL3 90.8 32.5 W T8 & 0.78 BF Elec 153.85 8.51 59.39 10.14 

EL3 91.2 34 W T12 & 0.86 BF Elec 179.58 ­17.22 71.89 5.97 

Retrofit

Ballast

Replacement EL4 92.3 32.5 W T8 & 0.75 BF Elec 148.79 13.56 59.64 11.04 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 146.22 16.14 60.15 12.09 EL4 93.0 26.6 W T8 & 0.88 BF Elec 136.79 25.56 62.41 14.00 EL5 95.4 32.5 W T8 & 0.71 BF Elec 144.49 17.87 60.58 12.23 EL5 96.0 28.4 W T8 & 0.78 BF Elec 140.78 21.57 59.79 13.82 

8B­36

EE-2006-STD-0131 COMMENT 37.2
Table 8B.17 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin System Operating i

Sector with Low Lamp Prices (continued)

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline 77.9 34 W T12 & 0.88 BF Elec 173.94 0.00 61.24 0.00 

EL1 82.4 34 W T12 & 0.86 BF Elec 174.18 ­0.24 63.45 0.46 

EL2 85.3 34 W T12 & 0.86 BF Elec 178.39 ­4.46 67.67 0.46 

EL2 86.2 32.5 W T8 & 0.88 BF Elec 163.48 10.45 55.22 1.64 

Event III: EL3 90.8 32.5 W T8 & 0.78 BF Elec 152.49 21.45 57.08 4.63 

Ballast Lamp & EL3 91.2 34 W T12 & 0.86 BF Elec 178.21 ­4.28 69.58 0.46 

Failure Ballast

Replacement EL4 92.3 32.5 W T8 & 0.75 BF Elec 147.43 26.50 57.33 5.52 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 144.85 29.08 57.84 6.58 EL4 93.0 26.6 W T8 & 0.88 BF Elec 135.43 38.50 60.10 8.48 EL5 95.4 32.5 W T8 & 0.71 BF Elec 143.12 30.81 58.27 6.72 EL5 96.0 28.4 W T8 & 0.78 BF Elec 139.42 34.52 57.48 8.30 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 164.85 0.00 57.52 0.00 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 153.85 20.09 59.39 4.63 

Event IV: EL4 92.3 32.5 W T8 & 0.75 BF Elec 148.79 25.14 59.64 5.52 

Ballast Lamp & EL4 93.8 30.4 W T8 & 0.78 BF Elec 146.22 27.72 60.15 6.58 

Retrofit Ballast

Replacement EL4 93.0 26.6 W T8 & 0.88 BF Elec 136.79 37.14 62.41 8.48 

EL5 95.4 32.5 W T8 & 0.71 BF Elec 144.49 29.45 60.58 6.72 EL5 96.0 28.4 W T8 & 0.78 BF Elec 140.78 33.15 59.79 8.30 

Table 8B.18 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin System Operating iSector with No Ballast Prices

Operating

Event Response Efficacy Level Rated Lamp Efficacy Design Option LCC LCC Savings Installed Price Cost Savings

(Start Year

8B­37

EE-2006-STD-0131 COMMENT 37.2
lms/W $ $ $ $ 

Event I:

Lamp Failure

Baseline Baseline 77.9 34 W T12 & 0.88 BF Mag 168.95 0.00 11.22 0.00 

B: Lamp &

Ballast

Replacement

EL1 82.4 34 W T12 & 0.88 BF Elec 148.88 20.06 14.91 5.52 

EL2 85.3 34 W T12 & 0.86 BF Elec 153.93 15.01 21.94 5.97 

EL2 86.2 32.5 W T8 & 0.88 BF Elec 138.86 30.09 11.97 7.16 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 129.10 39.84 15.07 10.14 

EL3 91.2 34 W T12 & 0.86 BF Elec 154.20 14.74 25.13 5.97 

EL4 92.3 32.5 W T8 & 0.75 BF Elec 123.82 45.13 15.50 11.04 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 121.98 46.97 16.35 12.09 EL4 93.0 26.6 W T8 & 0.88 BF Elec 112.87 56.08 20.11 14.00 EL5 95.4 32.5 W T8 & 0.71 BF Elec 120.06 48.88 17.06 12.23 EL5 96.0 28.4 W T8 & 0.78 BF Elec 116.97 51.98 15.74 13.82 

Baseline Baseline 77.9 34 W T12 & 0.88 BF Mag 163.39 0.00 11.22 0.00 

EL1 82.4 34 W T12 & 0.88 BF Elec 148.88 14.51 14.91 5.52 

EL2 85.3 34 W T12 & 0.86 BF Elec 153.93 9.45 21.94 5.97 

EL2 86.2 32.5 W T8 & 0.88 BF Elec 138.86 24.53 11.97 7.16 

Event II:

Standards

Induced

Lamp &

EL3 90.8 32.5 W T8 & 0.78 BF Elec 129.10 34.28 15.07 10.14 

EL3 91.2 34 W T12 & 0.86 BF Elec 154.20 9.19 25.13 5.97 

Retrofit

Ballast

Replacement EL4 92.3 32.5 W T8 & 0.75 BF Elec 123.82 39.57 15.50 11.04 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 121.98 41.41 16.35 12.09 EL4 93.0 26.6 W T8 & 0.88 BF Elec 112.87 50.52 20.11 14.00 EL5 95.4 32.5 W T8 & 0.71 BF Elec 120.06 43.32 17.06 12.23 EL5 96.0 28.4 W T8 & 0.78 BF Elec 116.97 46.42 15.74 13.82 

Table 8B.18 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin System Operating i

Sector with No Ballast Prices (continued)

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost Savings

(Start Year)

$

Payb

Per

y

Event III:

Ballast

Baseline Baseline 77.9 34 W T12 & 0.88 BF Elec 145.19 0.00 11.22 0.00 N

Lamp & EL1 82.4 34 W T12 & 0.86 BF Elec 146.91 ­1.72 14.91 0.46 8

8B­38

EE-2006-STD-0131 COMMENT 37.2
Failure Ballast EL2 85.3 34 W T12 & 0.86 BF Elec 153.93 ­8.74 21.94 0.46 23

Replacement EL2 86.2 32.5 W T8 & 0.88 BF Elec 138.86 6.33 11.97 1.64 0

EL3 90.8 32.5 W T8 & 0.78 BF Elec 129.10 16.09 15.07 4.63 0

EL3 91.2 34 W T12 & 0.86 BF Elec 154.20 ­9.01 25.13 0.46 30

EL4 92.3 32.5 W T8 & 0.75 BF Elec 123.82 21.38 15.50 5.52 0

EL4 93.8 30.4 W T8 & 0.78 BF Elec 121.98 23.21 16.35 6.58 0EL4 93.0 26.6 W T8 & 0.88 BF Elec 112.87 32.33 20.11 8.48 1EL5 95.4 32.5 W T8 & 0.71 BF Elec 120.06 25.13 17.06 6.72 0EL5 96.0 28.4 W T8 & 0.78 BF Elec 116.97 28.22 15.74 8.30 0

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 138.86 0.00 11.97 0.00 N

EL3 90.8 32.5 W T8 & 0.78 BF Elec 129.10 16.09 15.07 4.63 0

Event IV: EL4 92.3 32.5 W T8 & 0.75 BF Elec 123.82 21.38 15.50 5.52 0

Ballast Lamp & EL4 93.8 30.4 W T8 & 0.78 BF Elec 121.98 23.21 16.35 6.58 0

Retrofit Ballast

Replacement EL4 93.0 26.6 W T8 & 0.88 BF Elec 112.87 32.33 20.11 8.48 1

EL5 95.4 32.5 W T8 & 0.71 BF Elec 120.06 25.13 17.06 6.72 0

EL5 96.0 28.4 W T8 & 0.78 BF Elec 116.97 28.22 15.74 8.30 0

8B­39

EE-2006-STD-0131 COMMENT 37.2
Table 8B.19 LCC and PBP Results for a Three­Lamp 4­Foot 32W T8 Medium Bipin System Operating in 

Sector with High Lamp Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating Cost

Savings (Start

Year)

$

P

P

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 141.07 0.00 14.18 0.00 

Event I:

Lamp

Failure

A: Lamp

Replacement

EL4 93.8 30.4 W T8 & 0.88 BF Elec 137.93 3.14 20.31 2.15 

EL4 93.0 26.6 W T8 & 0.88 BF Elec 117.13 23.94 25.58 6.84 

EL5 96.0 28.4 W T8 & 0.88 BF Elec 132.56 8.51 19.47 4.06 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 167.90 0.00 59.64 0.00 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 159.39 8.51 63.98 2.99 

Event III: EL4 92.3 32.5 W T8 & 0.75 BF Elec 153.87 14.03 64.58 3.88 

Ballast Lamp & EL4 93.8 30.4 W T8 & 0.78 BF Elec 152.78 15.13 65.77 4.94 

Failure Ballast

Replacement EL4 93.0 26.6 W T8 & 0.88 BF Elec 143.97 23.94 71.04 6.84 

EL5 95.4 32.5 W T8 & 0.75 BF Elec 155.82 12.09 66.77 3.88 EL5 96.0 28.4 W T8 & 0.88 BF Elec 159.39 8.51 64.93 4.06 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 169.27 0.00 61.95 0.00 

Event V:

New

EL3 90.8 32.5 W T8 & 0.78 BF Elec 160.75 8.51 66.29 2.99 

EL4 92.3 32.5 W T8 & 0.75 BF Elec 155.23 14.03 66.89 3.88 

Construction New Lamp EL4 93.8 30.4 W T8 & 0.78 BF Elec 154.14 15.13 68.08 4.94 

and

Renovation

& Ballast

Purchase EL4 93.0 26.6 W T8 & 0.88 BF Elec 145.33 23.94 73.34 6.84 

EL5 95.4 32.5 W T8 & 0.75 BF Elec 157.18 12.09 69.08 3.88 EL5 96.0 28.4 W T8 & 0.88 BF Elec 160.75 8.51 67.23 4.06 

8B­40

EE-2006-STD-0131 COMMENT 37.2
Table 8B.20 LCC and PBP Results for a Three­Lamp 4­Foot 32W T8 Medium Bipin System Operating in 

Sector with Low Lamp Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating Cost

Savings (Start

Year)

$

P

P

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 136.65 0.00 9.76 0.00 

Event I:

Lamp

Failure

A: Lamp

Replacement

EL4 93.8 30.4 W T8 & 0.88 BF Elec 130.01 6.64 12.38 2.15 

EL4 93.0 26.6 W T8 & 0.88 BF Elec 108.60 28.05 14.64 6.84 

EL5 96.0 28.4 W T8 & 0.88 BF Elec 123.79 12.86 12.02 4.06 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 163.48 0.00 55.22 0.00 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 152.49 11.00 57.08 2.99 

Event III: EL4 92.3 32.5 W T8 & 0.75 BF Elec 147.43 16.05 57.33 3.88 

Ballast Lamp & EL4 93.8 30.4 W T8 & 0.78 BF Elec 144.85 18.63 57.84 4.94 

Failure Ballast

Replacement EL4 93.0 26.6 W T8 & 0.88 BF Elec 135.43 28.05 60.10 6.84 

EL5 95.4 32.5 W T8 & 0.75 BF Elec 148.27 15.22 58.27 3.88 EL5 96.0 28.4 W T8 & 0.88 BF Elec 150.62 12.86 57.48 4.06 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 164.85 0.00 57.52 0.00 

Event V:

New

EL3 90.8 32.5 W T8 & 0.78 BF Elec 153.85 11.00 59.39 2.99 

EL4 92.3 32.5 W T8 & 0.75 BF Elec 148.79 16.05 59.64 3.88 

Construction New Lamp EL4 93.8 30.4 W T8 & 0.78 BF Elec 146.22 18.63 60.15 4.94 

and

Renovation

& Ballast

Purchase EL4 93.0 26.6 W T8 & 0.88 BF Elec 136.79 28.05 62.41 6.84 

EL5 95.4 32.5 W T8 & 0.75 BF Elec 149.63 15.22 60.58 3.88 EL5 96.0 28.4 W T8 & 0.88 BF Elec 151.99 12.86 59.79 4.06 

Table 8B.21 LCC and PBP Results for a 3­Lamp 4­foot 32W T8 Medium Bipin System Operating in the C

with No Ballast Price

8B­41

EE-2006-STD-0131 COMMENT 37.2
Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 138.86 0.00 11.97 0.00 

Event I:

Lamp

Failure

A: Lamp

Replacement

EL4 93.8 30.4 W T8 & 0.88 BF Elec 133.97 4.89 16.35 2.15 

EL4 93.0 26.6 W T8 & 0.88 BF Elec 112.87 25.99 20.11 6.84 

EL5 96.0 28.4 W T8 & 0.88 BF Elec 128.17 10.69 15.74 4.06 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 138.86 0.00 11.97 0.00 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 129.10 9.76 15.07 2.99 

Event III: EL4 92.3 32.5 W T8 & 0.75 BF Elec 123.82 15.04 15.50 3.88 

Ballast Lamp & EL4 93.8 30.4 W T8 & 0.78 BF Elec 121.98 16.88 16.35 4.94 

Failure Ballast

Replacement EL4 93.0 26.6 W T8 & 0.88 BF Elec 112.87 25.99 20.11 6.84 

EL5 95.4 32.5 W T8 & 0.75 BF Elec 125.21 13.65 17.06 3.88 EL5 96.0 28.4 W T8 & 0.88 BF Elec 128.17 10.69 15.74 4.06 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 138.86 0.00 11.97 0.00 

Event V:

New

EL3 90.8 32.5 W T8 & 0.78 BF Elec 129.10 9.76 15.07 2.99 

EL4 92.3 32.5 W T8 & 0.75 BF Elec 123.82 15.04 15.50 3.88 

Construction New Lamp & EL4 93.8 30.4 W T8 & 0.78 BF Elec 121.98 16.88 16.35 4.94 

and

Renovation

Ballast

Purchase EL4 93.0 26.6 W T8 & 0.88 BF Elec 112.87 25.99 20.11 6.84 

EL5 95.4 32.5 W T8 & 0.75 BF Elec 125.21 13.65 17.06 3.88 EL5 96.0 28.4 W T8 & 0.88 BF Elec 128.17 10.69 15.74 4.06 

For the 4­foot medium bipin product class with CCT less than or equal to 4,500K in the residential sector

baseline lamp: a 40W T12. The following tables present the LCC savings and PBP results for this 4­foot mediu

operating in the residential sector with high lamp prices, low lamp prices, and no ballast price. Key inputs consi

AEO2008 reference case electricity prices. For the lamp failure event, residential high operating hours (of 1,210 

used, and the analysis period is 2.5 years. For other events, residential average operating hours (of 789 hours per 

the analysis period is 15 years.

8B­42

EE-2006-STD-0131 COMMENT 37.2
Table 8B.22 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin System Operating in 

Sector with High Lamp Prices and Average Operating Hours

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 76.8 41 W T12 & 0.68 BF Mag 112.31 0.00 51.07 

EL1 80.5 41 W T12 & 0.65 BF Elec 105.51 6.80 54.77 

EL1 82.4 34 W T12 & 0.85 BF Elec 103.72 8.59 49.48 EL1 82.9 41 W T12 & 0.65 BF Elec 109.85 2.46 59.11 EL2 85.3 34 W T12 & 0.75 BF Elec 98.03 14.28 56.04 EL2 86.2 32.5 W T8 & 0.78 BF Elec 95.29 17.01 50.11 

Event III:

Ballast Failure Lamp & Ballast

EL2 87.8 41 W T12 & 0.65 BF Elec 110.12 2.19 59.38 

EL3 91.2 34 W T12 & 0.66 BF Mag 115.42 ­3.11 62.93 

Replacement EL3 91.2 34 W T12 & 0.75 BF Elec 101.01 11.30 59.02 

EL3 90.8 32.5 W T8 & 0.75 BF Elec 96.38 15.93 53.01 EL4 92.3 32.5 W T8 & 0.75 BF Elec 96.77 15.53 53.40 EL4 93.8 30.4 W T8 & 0.75 BF Elec 95.49 16.82 54.20 EL4 93.0 26.6 W T8 & 0.78 BF Elec 93.11 19.20 57.71 EL5 95.4 32.5 W T8 & 0.71 BF Elec 95.82 16.49 54.86 EL5 96.0 28.4 W T8 & 0.78 BF Elec 93.53 18.78 53.64 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 103.65 0.00 52.42 

EL3 91.2 34 W T12 & 0.75 BF Elec 103.32 0.33 61.32 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 100.50 3.15 55.32 

Event V: New

Construction

and Renovation

New Lamp &

Ballast

Purchase

EL4 92.3 32.5 W T8 & 0.78 BF Elec 100.90 2.75 55.71 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 99.29 4.35 56.51 

EL4 93.0 26.6 W T8 & 0.88 BF Elec 99.73 3.92 60.02 EL5 95.4 32.5 W T8 & 0.75 BF Elec 100.54 3.10 57.17 EL5 96.0 28.4 W T8 & 0.78 BF Elec 95.84 7.81 55.95 

8B­43

EE-2006-STD-0131 COMMENT 37.2
Table 8B.23 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin System Operating in 

Sector with Low Lamp Prices and Average Operating Hours

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 76.8 41 W T12 & 0.68 BF Mag 109.12 0.00 47.88 

EL1 80.5 41 W T12 & 0.65 BF Elec 97.97 11.15 47.23 

EL1 82.4 34 W T12 & 0.85 BF Elec 99.20 9.92 44.96 EL1 82.9 41 W T12 & 0.65 BF Elec 99.83 9.29 49.09 EL2 85.3 34 W T12 & 0.75 BF Elec 89.76 19.36 47.77 EL2 86.2 32.5 W T8 & 0.78 BF Elec 92.35 16.78 47.16 

Event III:

Ballast Failure Lamp & Ballast

EL2 87.8 41 W T12 & 0.65 BF Elec 99.95 9.18 49.21 

EL3 91.2 34 W T12 & 0.66 BF Mag 105.45 3.67 52.96 

Replacement EL3 91.2 34 W T12 & 0.75 BF Elec 91.04 18.08 49.05 

EL3 90.8 32.5 W T8 & 0.75 BF Elec 91.77 17.35 48.41 EL4 92.3 32.5 W T8 & 0.75 BF Elec 91.94 17.18 48.58 EL4 93.8 30.4 W T8 & 0.75 BF Elec 90.21 18.91 48.92 EL4 93.0 26.6 W T8 & 0.78 BF Elec 85.82 23.30 50.42 EL5 95.4 32.5 W T8 & 0.71 BF Elec 90.15 18.97 49.20 EL5 96.0 28.4 W T8 & 0.78 BF Elec 88.57 20.56 48.67 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 100.70 0.00 49.47 

EL3 91.2 34 W T12 & 0.75 BF Elec 93.35 7.35 51.36 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 95.90 4.80 50.71 

Event V: New

Construction

and Renovation

New Lamp &

Ballast

Purchase

EL4 92.3 32.5 W T8 & 0.78 BF Elec 96.07 4.63 50.88 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 94.01 6.69 51.22 

EL4 93.0 26.6 W T8 & 0.88 BF Elec 92.44 8.26 52.73 EL5 95.4 32.5 W T8 & 0.75 BF Elec 94.88 5.82 51.51 EL5 96.0 28.4 W T8 & 0.78 BF Elec 90.87 9.82 50.98 

8B­44

EE-2006-STD-0131 COMMENT 37.2
Table 8B.24 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin System Operating in 

Sector with No Ballast Price and Average Operating Hours

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 76.8 41 W T12 & 0.68 BF Mag 65.22 0.00 3.98 

EL1 80.5 41 W T12 & 0.65 BF Elec 60.17 5.05 9.43 

EL1 82.4 34 W T12 & 0.85 BF Elec 59.89 5.33 5.65 EL1 82.9 41 W T12 & 0.65 BF Elec 63.26 1.95 12.52 EL2 85.3 34 W T12 & 0.75 BF Elec 52.32 12.89 10.33 EL2 86.2 32.5 W T8 & 0.78 BF Elec 48.87 16.35 3.68 

Event III:

Ballast Failure Lamp & Ballast

EL2 87.8 41 W T12 & 0.65 BF Elec 63.46 1.76 12.72 

EL3 91.2 34 W T12 & 0.66 BF Mag 64.95 0.27 12.46 

Replacement EL3 91.2 34 W T12 & 0.75 BF Elec 54.45 10.77 12.46 

EL3 90.8 32.5 W T8 & 0.75 BF Elec 49.12 16.09 5.75 EL4 92.3 32.5 W T8 & 0.75 BF Elec 49.41 15.81 6.04 EL4 93.8 30.4 W T8 & 0.75 BF Elec 47.90 17.32 6.60 EL4 93.0 26.6 W T8 & 0.78 BF Elec 44.51 20.70 9.11 EL5 95.4 32.5 W T8 & 0.71 BF Elec 48.03 17.19 7.08 EL5 96.0 28.4 W T8 & 0.78 BF Elec 46.09 19.12 6.20 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 54.91 0.00 3.68 

EL3 91.2 34 W T12 & 0.75 BF Elec 54.45 0.46 12.46 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 50.94 3.97 5.75 

Event V: New

Construction

and Renovation

New Lamp &

Ballast

Purchase

EL4 92.3 32.5 W T8 & 0.78 BF Elec 51.22 3.69 6.04 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 49.39 5.52 6.60 EL4 93.0 26.6 W T8 & 0.88 BF Elec 48.82 6.09 9.11 EL5 95.4 32.5 W T8 & 0.75 BF Elec 50.45 4.46 7.08 EL5 96.0 28.4 W T8 & 0.78 BF Elec 46.09 8.82 6.20 

8B­45

EE-2006-STD-0131 COMMENT 37.2
Table 8B.25 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin System Operating in 

Sector with High Lamp Prices and High Operating Hours

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

S

(

Y

Baseline Baseline 76.8 41 W T12 & 0.68 BF Mag 27.03 0.00 5.58 

A: Lamp

Replacement EL3 91.2 34 W T12 & 0.66 BF Mag 35.83 ­8.79 17.44 

EL1 80.5 41 W T12 & 0.65 BF Elec 33.79 ­6.75 54.77 

EL1 82.4 34 W T12 & 0.85 BF Elec 33.46 ­6.43 49.48 EL1 82.9 41 W T12 & 0.65 BF Elec 35.05 ­8.02 59.11 EL2 85.3 34 W T12 & 0.75 BF Elec 31.09 ­4.06 56.04 EL2 86.2 32.5 W T8 & 0.78 BF Elec 30.48 ­3.44 50.11 

Event I: Lamp

Failure B: Lamp and

Ballast

Replacement

EL2 87.8 41 W T12 & 0.65 BF Elec 35.13 ­8.10 59.38 

EL3 91.2 34 W T12 & 0.66 BF Mag 36.78 ­9.75 62.93 EL3 91.2 34 W T12 & 0.75 BF Elec 31.96 ­4.93 59.02 EL3 90.8 32.5 W T8 & 0.75 BF Elec 30.69 ­3.65 53.01 EL4 92.3 32.5 W T8 & 0.75 BF Elec 30.80 ­3.77 53.40 EL4 93.8 30.4 W T8 & 0.75 BF Elec 30.31 ­3.28 54.20 EL4 93.0 26.6 W T8 & 0.78 BF Elec 29.27 ­2.24 57.71 EL5 95.4 32.5 W T8 & 0.71 BF Elec 30.38 ­3.35 54.86 EL5 96.0 28.4 W T8 & 0.78 BF Elec 29.65 ­2.62 53.64 

8B­46

EE-2006-STD-0131 COMMENT 37.2
Table 8B.26 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin System Operating in 

Sector with Low Lamp Prices and High Operating Hours

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 76.8 41 W T12 & 0.68 BF Mag 23.85 0.00 2.40 

A: Lamp

Replacement EL3 91.2 34 W T12 & 0.66 BF Mag 25.86 ­2.01 7.47 

EL1 80.5 41 W T12 & 0.65 BF Elec 31.58 ­7.73 47.23 

EL1 82.4 34 W T12 & 0.85 BF Elec 32.14 ­8.30 44.96 EL1 82.9 41 W T12 & 0.65 BF Elec 32.12 ­8.28 49.09 EL2 85.3 34 W T12 & 0.75 BF Elec 28.68 ­4.83 47.77 EL2 86.2 32.5 W T8 & 0.78 BF Elec 29.62 ­5.77 47.16 

Event I: Lamp

Failure B: Lamp and

Ballast

Replacement

EL2 87.8 41 W T12 & 0.65 BF Elec 32.16 ­8.31 49.21 

EL3 91.2 34 W T12 & 0.66 BF Mag 33.87 ­10.02 52.96 

EL3 91.2 34 W T12 & 0.75 BF Elec 29.05 ­5.20 49.05 

EL3 90.8 32.5 W T8 & 0.75 BF Elec 29.34 ­5.50 48.41 EL4 92.3 32.5 W T8 & 0.75 BF Elec 29.39 ­5.55 48.58 EL4 93.8 30.4 W T8 & 0.75 BF Elec 28.77 ­4.92 48.92 EL4 93.0 26.6 W T8 & 0.78 BF Elec 27.14 ­3.29 50.42 

EL5 95.4 32.5 W T8 & 0.71 BF Elec 28.73 ­4.88 49.20 

EL5 96.0 28.4 W T8 & 0.78 BF Elec 28.20 ­4.36 48.67 

8B­47

EE-2006-STD-0131 COMMENT 37.2
Table 8B.27 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin System Operating in 

Sector with No Ballast Price and High Operating Hours

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 76.8 41 W T12 & 0.68 BF Mag 25.43 0.00 3.98 

A: Lamp

Replacement EL3 91.2 34 W T12 & 0.66 BF Mag 30.85 ­5.42 12.46 

EL1 80.5 41 W T12 & 0.65 BF Elec 20.53 4.90 9.43 EL1 82.4 34 W T12 & 0.85 BF Elec 20.65 4.78 5.65 EL1 82.9 41 W T12 & 0.65 BF Elec 21.44 3.99 12.52 EL2 85.3 34 W T12 & 0.75 BF Elec 17.73 7.70 10.33 EL2 86.2 32.5 W T8 & 0.78 BF Elec 16.90 8.53 3.68 

Event I: Lamp

Failure B: Lamp and

Ballast

Replacement

EL2 87.8 41 W T12 & 0.65 BF Elec 21.49 3.94 12.72 

EL3 91.2 34 W T12 & 0.66 BF Mag 22.03 3.40 12.46 EL3 91.2 34 W T12 & 0.75 BF Elec 18.35 7.08 12.46 EL3 90.8 32.5 W T8 & 0.75 BF Elec 16.87 8.56 5.75 EL4 92.3 32.5 W T8 & 0.75 BF Elec 16.96 8.47 6.04 EL4 93.8 30.4 W T8 & 0.75 BF Elec 16.40 9.03 6.60 EL4 93.0 26.6 W T8 & 0.78 BF Elec 15.06 10.37 9.11 EL5 95.4 32.5 W T8 & 0.71 BF Elec 16.42 9.02 7.08 EL5 96.0 28.4 W T8 & 0.78 BF Elec 15.79 9.64 6.20 

8B.7.2.2 Product Class: 4­foot T5 miniature bipin high output ≤ 4,500K

For the 4­foot T5 miniature bipin high output product class with CCT less than or equal to 4,500K in the 

DOE analyzed one baseline lamp: a 54W T5. For this baseline, the analysis period is 3.9 years. Other key input

AEO2008 reference case electricity prices. The following table presents the LCC savings and PBP results for the 

high lamp prices, low lamp prices, and no ballast price.

8B­48

EE-2006-STD-0131 COMMENT 37.2
Table 8B.28 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin High Output System Oper

Industrial Sector with High Lamp Prices

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 126.44 0.00 12.08 

A: Lamp

Replacement EL1 98.0 51 W T5 & 1 BF Elec 132.81 ­6.36 25.26 

Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 157.99 0.00 70.67 

Event III:

Ballast Failure Lamp and Ballast

Replacement

EL1 98.0 51 W T5 & 1 BF Elec 164.35 ­6.36 83.85 

Event V: New Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 159.23 0.00 72.98 

Construction New Lamp & EL1 92.9 53.8 W T5 & 1 BF Elec 104.28 54.95 80.02 1

and Renovation Ballast

Purchase EL1 98.0 51 W T5 & 1 BF Elec 103.86 55.37 86.16 1

8B­49

EE-2006-STD-0131 COMMENT 37.2
Table 8B.29 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin High Output System Oper

Industrial Sector with Low Lamp Prices

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 123.15 0.00 8.79 

A: Lamp

Replacement EL1 98.0 51 W T5 & 1 BF Elec 123.63 ­0.48 14.43 

Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 154.69 0.00 67.38 

Event III:

Ballast Failure Lamp and Ballast

Replacement

EL1 98.0 51 W T5 & 1 BF Elec 155.18 ­0.48 73.02 

Event V: New Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 155.94 0.00 69.69 

Construction New Lamp & EL1 92.9 53.8 W T5 & 1 BF Elec 99.69 56.25 72.70 1

and Renovation Ballast

Purchase EL1 98.0 51 W T5 & 1 BF Elec 98.10 57.83 75.33 1

8B­50

EE-2006-STD-0131 COMMENT 37.2
Table 8B.30 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin High Output System Oper

Industrial Sector with No Ballast Price

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 124.80 0.00 10.44 

A: Lamp

Replacement EL1 98.0 51 W T5 & 1 BF Elec 128.22 ­3.42 19.85 

Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 124.80 0.00 10.44 

Event III:

Ballast Failure Lamp and Ballast

Replacement

EL1 98.0 51 W T5 & 1 BF Elec 128.22 ­3.42 19.85 

Event V: New Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 124.80 0.00 10.44 

Construction New Lamp & EL1 92.9 53.8 W T5 & 1 BF Elec 81.42 43.38 15.46 1

and Renovation Ballast

Purchase EL1 98.0 51 W T5 & 1 BF Elec 80.42 44.38 19.85 1

8B.7.2.3 Product Class: 4­foot T5 miniature bipin standard output ≤ 4,500K

For the 4­foot T5 miniature bipin standard output product class with CCT less than or equal to 4,500K in 

sector, DOE analyzed one baseline lamp: a 28W T5. For this baseline, the analysis period is 5.5 years. Other ke

using AEO2008 reference case electricity prices. The following table presents the LCC savings and PBP results 

with high lamp prices, low lamp prices, and no ballast price.

8B­51

EE-2006-STD-0131 COMMENT 37.2
Table 8B.31 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin Standard Output System O

Commercial Sector with High Lamp Prices

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 113.88 0.00 10.63 

A: Lamp

Replacement EL2 111.5 26 W T5 & 1.15 BF Elec 114.41 ­0.53 18.28 

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 147.82 0.00 68.13 

Event III: EL1 104.3 27.8 W T5 & 0.95 BF Elec 139.34 8.48 73.39 

Ballast Failure Lamp & Ballast

Replacement EL2 109.7 27.8 W T5 & 0.9 BF Elec 138.98 8.84 76.46 

EL2 111.5 26 W T5 & 0.9 BF Elec 129.31 18.51 75.78 

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 149.19 0.00 70.44 

Event V: New

Construction

and Renovation

New Lamp &

Ballast

Purchase

EL1 104.3 27.8 W T5 & 0.95 BF Elec 107.19 42.00 75.70 

EL2 109.7 27.8 W T5 & 0.9 BF Elec 103.59 45.60 78.77 EL2 111.5 26 W T5 & 0.9 BF Elec 105.08 44.10 78.09 

8B­52

EE-2006-STD-0131 COMMENT 37.2
Table 8B.32 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin Standard Output System O

Commercial Sector with Low Lamp Prices

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 111.40 0.00 8.15 

A: Lamp

Replacement EL2 111.5 26 W T5 & 1.15 BF Elec 108.44 2.97 11.44 

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 145.34 0.00 65.65 

Event III: EL1 104.3 27.8 W T5 & 0.95 BF Elec 133.86 11.48 67.91 

Ballast Failure Lamp & Ballast

Replacement EL2 109.7 27.8 W T5 & 0.9 BF Elec 131.75 13.60 69.23 

EL2 111.5 26 W T5 & 0.9 BF Elec 123.34 22.00 68.94 

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 146.71 0.00 67.95 

Event V: New

Construction

and Renovation

New Lamp &

Ballast

Purchase

EL1 104.3 27.8 W T5 & 0.95 BF Elec 103.02 43.69 70.22 

EL2 109.7 27.8 W T5 & 0.9 BF Elec 98.25 48.46 71.54 EL2 111.5 26 W T5 & 0.9 BF Elec 100.28 46.43 71.25 

8B­53

EE-2006-STD-0131 COMMENT 37.2
Table 8B.33 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin Standard Output System O

Commercial Sector with No Ballast Price

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 112.64 0.00 9.39 

A: Lamp

Replacement EL2 111.5 26 W T5 & 1.15 BF Elec 111.42 1.22 14.86 

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 112.64 0.00 9.39 

Event III: EL1 104.3 27.8 W T5 & 0.95 BF Elec 102.66 9.98 13.15 

Ballast Failure Lamp & Ballast

Replacement EL2 109.7 27.8 W T5 & 0.9 BF Elec 101.42 11.22 15.35 

EL2 111.5 26 W T5 & 0.9 BF Elec 92.39 20.26 14.86 

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 112.64 0.00 9.39 

Event V: New

Construction

and Renovation

New Lamp &

Ballast

Purchase

EL1 104.3 27.8 W T5 & 0.95 BF Elec 78.21 34.43 13.15 

EL2 109.7 27.8 W T5 & 0.9 BF Elec 74.86 37.78 15.35 EL2 111.5 26 W T5 & 0.9 BF Elec 74.29 38.35 14.86 

8B.7.2.4 Product Class: 8­foot single pin slimline ≤ 4,500K

The following tables present the findings of an LCC analysis on the three 8­foot single pin slimline GSFL 

in the commercial sector with a CCT less than or equal to 4,500K, considering low lamp prices, high lamp prices

Key inputs consist of using AEO2008 reference case electricity prices and an analysis period of 4.0 years. Note: 

results in Event I are not shown for a 60W T12 lamp because there are no energy saving lamp replacement option

8B­54

EE-2006-STD-0131 COMMENT 37.2
Table 8B.34 LCC and PBP Results for a Two­Lamp 8­Foot 75W T12 Single Pin Slimline System Operatin

Commercial Sector with High Lamp Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline 85.6 75 W T12 & 0.94 BF Mag 203.66 0.00 20.84 0.00 

A: Lamp

Replacement EL3 97.5 60.5 W T12 & 0.88 BF Mag 167.09 36.57 25.42 10.80 

Event I: Baseline 85.6 75 W T12 & 0.94 BF Mag 203.66 0.00 20.84 0.00 

Lamp Failure B: Lamp & EL1 87.3 75 W T12 & 0.85 BF Elec 218.58 ­14.93 102.54 8.77 

Ballast EL2 92.0 75 W T12 & 0.85 BF Elec 213.58 ­9.93 105.20 8.77 

Replacement EL3 94.8 60.1 W T8 & 1.18 BF Elec 228.17 ­24.52 113.18 2.72 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 181.58 22.08 98.57 15.24 

Baseline Baseline 85.6 75 W T12 & 0.94 BF Mag 192.53 0.00 20.84 0.00 

Event II:

Standards

Induced

Lamp &

EL1 87.3 75 W T12 & 0.85 BF Elec 219.62 ­27.09 104.85 8.77 

EL2 92.0 75 W T12 & 0.85 BF Elec 214.63 ­22.09 107.51 8.77 

Retrofit

Ballast

Replacement EL3 94.8 60.1 W T8 & 1.18 BF Elec 229.21 ­36.68 115.49 2.72 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 182.62 9.92 100.87 15.24 

Baseline Baseline 85.6 75 W T12 & 0.88 BF Elec 210.83 0.00 93.62 0.00 

Event III:

Ballast

Failure

Lamp &

Ballast

EL1 87.3 75 W T12 & 0.85 BF Elec 218.58 ­7.76 102.54 1.01 

EL2 92.0 75 W T12 & 0.85 BF Elec 213.58 ­2.76 105.20 1.01 

Replacement EL5 101.5 60.1 W T8 & 0.88 BF Elec 181.58 29.25 98.57 7.48 

Event IV: Baseline Baseline/EL3 94.8 60.1 W T8 & 1.18 BF Elec 229.21 0.00 115.49 0.00 

Ballast

Retrofit

Lamp &

Ballast

Replacement

EL5 101.5 60.1 W T8 & 0.88 BF Elec 182.62 46.60 100.87 12.52 

8B­55

EE-2006-STD-0131 COMMENT 37.2
Table 8B.35 LCC and PBP Results for a Two­Lamp 8­Foot 75W T12 Single Pin Slimline System Operatin

Commercial Sector with Low Lamp Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline 85.6 75 W T12 & 0.94 BF Mag 192.01 0.00 11.48 0.00 

A: Lamp

Replacement EL3 97.5 60.5 W T12 & 0.88 BF Mag 155.11 36.90 13.44 10.80 

Event I: Baseline 85.6 75 W T12 & 0.94 BF Mag 192.01 0.00 11.48 0.00 

Lamp Failure B: Lamp & EL1 87.3 75 W T12 & 0.85 BF Elec 200.60 ­8.58 88.08 8.77 

Ballast EL2 92.0 75 W T12 & 0.85 BF Elec 197.61 ­5.60 89.22 8.77 

Replacement EL3 94.8 60.1 W T8 & 1.18 BF Elec 221.55 ­29.54 106.56 2.72 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 171.54 20.47 87.07 15.24 

Baseline Baseline 85.6 75 W T12 & 0.94 BF Mag 185.57 0.00 11.48 0.00 

Event II:

Standards

Induced

Lamp &

EL1 87.3 75 W T12 & 0.85 BF Elec 201.64 ­16.06 90.39 8.77 

EL2 92.0 75 W T12 & 0.85 BF Elec 198.65 ­13.08 91.53 8.77 

Retrofit

Ballast

Replacement EL3 94.8 60.1 W T8 & 1.18 BF Elec 222.59 ­37.02 108.87 2.72 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 172.58 12.99 89.38 15.24 

Baseline Baseline 85.6 75 W T12 & 0.88 BF Elec 199.18 0.00 84.26 0.00 

Event III:

Ballast

Failure

Lamp &

Ballast

EL1 87.3 75 W T12 & 0.85 BF Elec 200.60 ­1.41 88.08 1.01 

EL2 92.0 75 W T12 & 0.85 BF Elec 197.61 1.57 89.22 1.01 

Replacement EL5 101.5 60.1 W T8 & 0.88 BF Elec 171.54 27.64 87.07 7.48 

Event IV: Baseline Baseline/EL3 94.8 60.1 W T8 & 1.18 BF Elec 222.59 0.00 108.87 0.00 

Ballast

Retrofit

Lamp &

Ballast

Replacement

EL5 101.5 60.1 W T8 & 0.88 BF Elec 172.58 50.01 89.38 12.52 

8B­56

EE-2006-STD-0131 COMMENT 37.2
Table 8B.36 LCC and PBP Results for a Two­Lamp 8­Foot 75W T12 Single Pin Slimline System Operatin

Commercial Sector with No Ballast Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline 85.6 75 W T12 & 0.94 BF Mag 197.83 0.00 16.16 0.00 

A: Lamp

Replacement EL3 97.5 60.5 W T12 & 0.88 BF Mag 161.10 36.73 19.43 10.80 

Event I: Baseline 85.6 75 W T12 & 0.94 BF Mag 197.83 0.00 16.16 0.00 

Lamp Failure B: Lamp & EL1 87.3 75 W T12 & 0.85 BF Elec 176.78 21.05 22.53 8.77 

Ballast EL2 92.0 75 W T12 & 0.85 BF Elec 172.79 25.05 24.43 8.77 

Replacement EL3 94.8 60.1 W T8 & 1.18 BF Elec 181.08 16.76 12.74 2.72 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 143.21 54.63 18.83 15.24 

Baseline Baseline 85.6 75 W T12 & 0.94 BF Mag 189.05 0.00 16.16 0.00 

Event II:

Standards

Induced

Lamp &

EL1 87.3 75 W T12 & 0.85 BF Elec 176.78 12.27 22.53 8.77 

EL2 92.0 75 W T12 & 0.85 BF Elec 172.79 16.26 24.43 8.77 

Retrofit

Ballast

Replacement EL3 94.8 60.1 W T8 & 1.18 BF Elec 181.08 7.98 12.74 2.72 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 143.21 45.84 18.83 15.24 

Baseline Baseline 85.6 75 W T12 & 0.88 BF Elec 172.20 0.00 16.16 0.00 

Event III:

Ballast

Failure

Lamp &

Ballast

EL1 87.3 75 W T12 & 0.85 BF Elec 176.78 ­4.59 22.53 1.01 

EL2 92.0 75 W T12 & 0.85 BF Elec 172.79 ­0.59 24.43 1.01 

Replacement EL5 101.5 60.1 W T8 & 0.88 BF Elec 143.21 28.99 18.83 7.48 

Event IV: Baseline Baseline/EL3 94.8 60.1 W T8 & 1.18 BF Elec 181.08 0.00 12.74 0.00 

Ballast

Retrofit

Lamp &

Ballast

Replacement

EL5 101.5 60.1 W T8 & 0.88 BF Elec 143.21 37.87 18.83 12.52 

8B­57

EE-2006-STD-0131 COMMENT 37.2
Table 8B.37 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin Slimline System Operatin

Commercial Sector with High Lamp Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Mag 159.57 0.00 14.07 0.00 

EL2 92.6 60.5 W T12 & 0.85 BF Elec 179.36 ­19.79 93.41 6.41 

Event I:

Lamp Failure B: Lamp &

EL3 97.5 60.5 W T12 & 0.85 BF Elec 178.72 ­19.15 98.20 6.41 

Ballast EL3 94.8 60.1 W T8 & 0.88 BF Elec 176.37 ­16.80 90.03 4.45 

Replacement

EL4 98.2 60.1 W T8 & 0.78 BF Elec 168.71 ­9.15 96.16 8.62 

EL5 101.8 57 W T8 & 0.78 BF Elec 164.77 ­5.20 96.70 7.93 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 167.79 ­8.22 98.57 8.62 

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Mag 151.83 0.00 14.07 0.00 

Event II:

Standards

Induced Lamp &

EL2 92.6 60.5 W T12 & 0.85 BF Elec 180.40 ­28.56 95.72 6.41 

EL3 97.5 60.5 W T12 & 0.85 BF Elec 179.76 ­27.93 100.51 6.41 

Retrofit Ballast

Replacement

EL3 94.8 60.1 W T8 & 0.88 BF Elec 177.41 ­25.58 92.34 4.45 

EL4 98.2 60.1 W T8 & 0.78 BF Elec 169.76 ­17.92 98.47 8.62 

EL5 101.8 57 W T8 & 0.78 BF Elec 165.81 ­13.98 99.01 7.93 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 168.83 ­17.00 100.87 8.62 

8B­58

EE-2006-STD-0131 COMMENT 37.2
Table 8B.37 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin Slimline System Operatin

Commercial Sector with High Lamp Prices (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Elec 174.54 0.00 86.85 

EL2 92.6 60.5 W T12 & 0.85 BF Elec 179.36 ­4.81 93.41 

Event III:

Ballast Failure Lamp & Ballast EL3 97.5 60.5 W T12 & 0.85 BF Elec 178.72 ­4.18 98.20 

Replacement EL4 98.2 60.1 W T8 & 0.78 BF Elec 168.71 5.83 96.16 

EL5 101.8 57 W T8 & 0.78 BF Elec 164.77 9.77 96.70 EL5 101.5 60.1 W T8 & 0.78 BF Elec 167.79 6.75 98.57 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 177.41 0.00 92.34 

Event IV: EL4 98.2 60.1 W T8 & 0.78 BF Elec 169.76 7.66 98.47 

Ballast Retrofit Lamp & Ballast

Replacement EL5 101.8 57 W T8 & 0.78 BF Elec 165.81 11.60 99.01 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 168.83 8.58 100.87 

8B­59

EE-2006-STD-0131 COMMENT 37.2
Table 8B.38 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin Slimline System Operatin

Commercial Sector with Low Lamp Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Mag 152.73 0.00 8.58 0.00 

EL2 92.6 60.5 W T12 & 0.85 BF Elec 167.86 ­15.13 84.17 6.41 

Event I:

Lamp Failure B: Lamp &

EL3 97.5 60.5 W T12 & 0.85 BF Elec 166.74 ­14.01 86.22 6.41 

Ballast EL3 94.8 60.1 W T8 & 0.88 BF Elec 169.75 ­17.02 83.41 4.45 

Replacement

EL4 98.2 60.1 W T8 & 0.78 BF Elec 158.59 ­5.86 86.04 8.62 

EL5 101.8 57 W T8 & 0.78 BF Elec 157.24 ­4.51 86.27 7.93 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 157.75 ­5.02 87.07 8.62 

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Mag 147.75 0.00 8.58 0.00 

Event II:

Standards

Induced Lamp &

EL2 92.6 60.5 W T12 & 0.85 BF Elec 168.90 ­21.16 86.48 6.41 

EL3 97.5 60.5 W T12 & 0.85 BF Elec 167.78 ­20.04 88.53 6.41 

Retrofit Ballast

Replacement

EL3 94.8 60.1 W T8 & 0.88 BF Elec 170.79 ­23.05 85.72 4.45 

EL4 98.2 60.1 W T8 & 0.78 BF Elec 159.63 ­11.88 88.35 8.62 

EL5 101.8 57 W T8 & 0.78 BF Elec 158.28 ­10.54 88.58 7.93 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 158.79 ­11.05 89.38 8.62 

8B­60

EE-2006-STD-0131 COMMENT 37.2
Table 8B.38 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin Slimline System Operatin

Commercial Sector with Low Lamp Prices (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Elec 167.71 0.00 81.36 

EL2 92.6 60.5 W T12 & 0.85 BF Elec 167.86 ­0.15 84.17 

Event III:

Ballast Failure Lamp & Ballast EL3 97.5 60.5 W T12 & 0.85 BF Elec 166.74 0.97 86.22 

Replacement EL4 98.2 60.1 W T8 & 0.78 BF Elec 158.59 9.12 86.04 

EL5 101.8 57 W T8 & 0.78 BF Elec 157.24 10.47 86.27 EL5 101.5 60.1 W T8 & 0.78 BF Elec 157.75 9.96 87.07 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 170.79 0.00 85.72 

Event IV: EL4 98.2 60.1 W T8 & 0.78 BF Elec 159.63 11.16 88.35 

Ballast Retrofit Lamp & Ballast

Replacement EL5 101.8 57 W T8 & 0.78 BF Elec 158.28 12.51 88.58 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 158.79 12.00 89.38 

8B­61

EE-2006-STD-0131 COMMENT 37.2
Table 8B.39 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin Slimline System Operatin

Commercial Sector with No Ballast Price

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Mag 156.15 0.00 11.33 0.00 

EL2 92.6 60.5 W T12 & 0.85 BF Elec 140.80 15.35 16.01 6.41 

Event I:

Lamp Failure B: Lamp &

EL3 97.5 60.5 W T12 & 0.85 BF Elec 139.92 16.23 19.43 6.41 

Ballast EL3 94.8 60.1 W T8 & 0.88 BF Elec 139.71 16.44 12.74 4.45 

Replacement

EL4 98.2 60.1 W T8 & 0.78 BF Elec 130.30 25.85 17.12 8.62 

EL5 101.8 57 W T8 & 0.78 BF Elec 127.66 28.50 17.50 7.93 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 129.42 26.73 18.83 8.62 

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Mag 149.79 0.00 11.33 0.00 

Event II:

Standards

Induced Lamp &

EL2 92.6 60.5 W T12 & 0.85 BF Elec 140.80 8.99 16.01 6.41 

EL3 97.5 60.5 W T12 & 0.85 BF Elec 139.92 9.87 19.43 6.41 

Retrofit Ballast

Replacement

EL3 94.8 60.1 W T8 & 0.88 BF Elec 139.71 10.08 12.74 4.45 

EL4 98.2 60.1 W T8 & 0.78 BF Elec 130.30 19.49 17.12 8.62 

EL5 101.8 57 W T8 & 0.78 BF Elec 127.66 22.13 17.50 7.93 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 129.42 20.37 18.83 8.62 

8B­62

EE-2006-STD-0131 COMMENT 37.2
Table 8B.39 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin Slimline System Operatin

Commercial Sector with No Ballast Price (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Elec 138.32 0.00 11.33 

EL2 92.6 60.5 W T12 & 0.85 BF Elec 140.80 ­2.48 16.01 

Event III:

Ballast Failure Lamp & Ballast EL3 97.5 60.5 W T12 & 0.85 BF Elec 139.92 ­1.61 19.43 

Replacement EL4 98.2 60.1 W T8 & 0.78 BF Elec 130.30 8.01 17.12 

EL5 101.8 57 W T8 & 0.78 BF Elec 127.66 10.66 17.50 EL5 101.5 60.1 W T8 & 0.78 BF Elec 129.42 8.90 18.83 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 139.71 0.00 12.74 

Event IV: EL4 98.2 60.1 W T8 & 0.78 BF Elec 130.30 9.41 17.12 

Ballast Retrofit Lamp & Ballast

Replacement EL5 101.8 57 W T8 & 0.78 BF Elec 127.66 12.06 17.50 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 129.42 10.29 18.83 

8B­63

EE-2006-STD-0131 COMMENT 37.2
Table 8B.40 LCC and PBP Results for a Two­Lamp 8­Foot 59W T8 Single Pin Slimline System Operating 

Sector with High Lamp Prices

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 143.02 0.00 16.05 

A: Lamp EL5 101.8 57 W T8 & 0.88 BF Elec 136.99 6.03 22.72 

Replacement EL5 103.6 55 W T8 & 0.88 BF Elec 133.56 9.46 21.57 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 176.37 0.00 90.03 

Event III:

Ballast Failure Lamp & Ballast

EL4 98.2 60.1 W T8 & 0.85 BF Elec 178.37 ­1.99 96.16 

EL5 101.8 57 W T8 & 0.85 BF Elec 168.67 7.70 96.70 

Replacement EL5 101.5 60.1 W T8 & 0.78 BF Elec 167.79 8.58 98.57 

EL5 103.6 55 W T8 & 0.88 BF Elec 166.91 9.46 95.56 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 177.41 0.00 92.34 

Event V: New EL4 98.2 60.1 W T8 & 0.85 BF Elec 179.41 ­1.99 98.47 

Construction New Lamp & EL5 101.8 57 W T8 & 0.85 BF Elec 169.71 7.70 99.01 

and Renovation Ballast

Purchase EL5 101.5 60.1 W T8 & 0.78 BF Elec 168.83 8.58 100.87 

EL5 103.6 55 W T8 & 0.88 BF Elec 167.95 9.46 97.86 

Event Response Efficacy Level

Rated

Lamp

Efficacy

Design Option LCC LCC Savings Installed Price

Oper

C

Sav

(St

Ye

lms/W $ $ $ 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 143.02 0.00 16.05 0

EL5 101.8 57 W T8 & 0.88 BF Elec 136.99 6.03 22.72 1

Event I: Lamp Failure A: Lamp

Replacement EL5 103.6 55 W T8 & 0.88 BF Elec 133.56 9.46 21.57 3

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 176.37 0.00 90.03 0

EL4 98.2 60.1 W T8 & 0.85 BF Elec 178.37 ­1.99 96.16 1

Event III:

Ballast Failure Lamp & Ballast

Replacement EL5 101.8 57 W T8 & 0.85 BF Elec 168.67 7.70 96.70 2

8B­64

EE-2006-STD-0131 COMMENT 37.2
EL5 101.5 60.1 W T8 & 0.78 BF Elec 167.79 8.58 98.57 4

EL5 103.6 55 W T8 & 0.88 BF Elec 166.91 9.46 95.56 3

Event V: New

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 177.41 0.00 92.34 0

EL4 98.2 60.1 W T8 & 0.85 BF Elec 179.41 ­1.99 98.47 1

Construction New Lamp & EL5 101.8 57 W T8 & 0.85 BF Elec 169.71 7.70 99.01 2

and Renovation Ballast

Purchase EL5 101.5 60.1 W T8 & 0.78 BF Elec 168.83 8.58 100.87 4

EL5 103.6 55 W T8 & 0.88 BF Elec 167.95 9.46 97.86 3

8B­65

EE-2006-STD-0131 COMMENT 37.2
Table 8B.41 LCC and PBP Results for a Two­Lamp 8­Foot 59W T8 Single Pin Slimline System Operating 

Sector with Low Lamp Prices

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 136.40 0.00 9.43 

A: Lamp EL5 101.8 57 W T8 & 0.88 BF Elec 129.47 6.93 12.29 

Replacement EL5 103.6 55 W T8 & 0.88 BF Elec 125.03 11.37 11.80 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 169.75 0.00 83.41 

Event III:

Ballast Failure Lamp & Ballast

EL4 98.2 60.1 W T8 & 0.85 BF Elec 168.24 1.51 86.04 

EL5 101.8 57 W T8 & 0.85 BF Elec 161.14 8.61 86.27 

Replacement EL5 101.5 60.1 W T8 & 0.78 BF Elec 157.75 12.00 87.07 

EL5 103.6 55 W T8 & 0.88 BF Elec 158.38 11.37 85.78 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 170.79 0.00 85.72 

Event V: New EL4 98.2 60.1 W T8 & 0.85 BF Elec 169.28 1.51 88.35 

Construction New Lamp & EL5 101.8 57 W T8 & 0.85 BF Elec 162.18 8.61 88.58 

and Renovation Ballast

Purchase EL5 101.5 60.1 W T8 & 0.78 BF Elec 158.79 12.00 89.38 

EL5 103.6 55 W T8 & 0.88 BF Elec 159.42 11.37 88.09 

8B­66

EE-2006-STD-0131 COMMENT 37.2
Table 8B.42 LCC and PBP Results for a Two­Lamp 8­Foot 59W T8 Single Pin Slimline System Operating 

Sector with No Ballast Prices

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 139.71 0.00 12.74 

A: Lamp EL5 101.8 57 W T8 & 0.88 BF Elec 133.23 6.48 17.50 

Replacement EL5 103.6 55 W T8 & 0.88 BF Elec 129.29 10.42 16.68 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 139.71 0.00 12.74 

Event III:

Ballast Failure Lamp & Ballast

EL4 98.2 60.1 W T8 & 0.85 BF Elec 139.95 ­0.24 17.12 

EL5 101.8 57 W T8 & 0.85 BF Elec 131.56 8.15 17.50 

Replacement EL5 101.5 60.1 W T8 & 0.78 BF Elec 129.42 10.29 18.83 

EL5 103.6 55 W T8 & 0.88 BF Elec 129.29 10.42 16.68 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 139.71 0.00 12.74 

Event V: New EL4 98.2 60.1 W T8 & 0.85 BF Elec 139.95 ­0.24 17.12 

Construction New Lamp & EL5 101.8 57 W T8 & 0.85 BF Elec 131.56 8.15 17.50 

and Renovation Ballast

Purchase EL5 101.5 60.1 W T8 & 0.78 BF Elec 129.42 10.29 18.83 

EL5 103.6 55 W T8 & 0.88 BF Elec 129.29 10.42 16.68 

8B.7.2.5 Product Class: 8­foot recessed double contact HO ≤ 4,500KThe following tables present the findings of an LCC analysis on the two 8­foot recessed double contact h

baselines operating in the industrial sector, considering low lamp prices, high lamp prices, or no ballast prices. K

using AEO2008 reference case electricity prices and an analysis period of 2.3 years. Note: Lamp replacement re

not shown for a 95W T12 lamp because there are no energy saving lamp replacement options.

8B­67

EE-2006-STD-0131 COMMENT 37.2
Table 8B.43 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double Contact HO Syste

Industrial Sector with High Lamp Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 168.23 0.00 25.25 0.00 

A: Lamp EL3 87.6 97 W T12 & 0.91 BF Mag 165.62 2.62 42.95 10.16 

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 166.49 1.74 43.82 10.16 

Event I: EL1 83.2 113 W T12 & 0.88 BF Elec 192.57 ­24.34 123.35 9.45 

Lamp Failure B: Lamp & EL3 87.6 97 W T12 & 0.91 BF Mag 191.34 ­23.11 120.80 10.16 

Ballast EL3 88.9 97 W T12 & 0.91 BF Mag 192.22 ­23.99 121.68 10.16 

Replacement EL3 88.9 97 W T12 & 0.9 BF Elec 183.20 ­14.97 125.77 15.34 

EL5 95.3 86 W T8 & 0.88 BF Elec 151.08 17.15 131.09 23.01 

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 154.85 0.00 25.25 0.00 

Event II:

Standards Lamp &

EL1 83.2 113 W T12 & 0.88 BF Elec 193.33 ­38.48 125.66 9.45 

EL3 87.6 97 W T12 & 0.91 BF Mag 192.11 ­37.25 123.11 10.16 

Induced

Retrofit

Ballast

Replacement

EL3 88.9 97 W T12 & 0.91 BF Mag 192.98 ­38.13 123.99 10.16 

EL3 88.9 97 W T12 & 0.9 BF Elec 183.96 ­29.11 128.08 15.34 EL5 95.3 86 W T8 & 0.88 BF Elec 151.84 3.01 133.40 23.01 

8B­68

EE-2006-STD-0131 COMMENT 37.2
Table 8B.43 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double Contact HO Syste

Industrial Sector with High Lamp Prices (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 193.96 0.00 103.11 

EL1 83.2 113 W T12 & 0.88 BF Elec 192.57 1.39 123.35 

Event III: EL3 87.6 97 W T12 & 0.91 BF Mag 191.34 2.62 120.80 1

Ballast Failure Lamp & Ballast

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 192.22 1.74 121.68 1

EL3 88.9 97 W T12 & 0.9 BF Elec 183.20 10.76 125.77 1EL5 95.3 86 W T8 & 0.88 BF Elec 151.08 42.88 131.09 2

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 194.72 0.00 105.41 

EL1 83.2 113 W T12 & 0.88 BF Elec 193.33 1.39 125.66 

EL2 86.1 97 W T12 & 0.9 BF Elec 189.72 5.00 109.95 EL2 86.1 97 W T12 & 0.91 BF Mag 197.84 ­3.12 105.86 

Event V: New EL3 87.6 97 W T12 & 0.9 BF Elec 205.76 ­11.04 127.21 

Construction New Lamp & EL3 87.6 97 W T12 & 0.91 BF Mag 192.11 2.62 123.11 1

and Renovation Ballast

Purchase EL3 88.9 97 W T12 & 0.9 BF Elec 183.96 10.76 128.08 1

EL3 88.9 97 W T12 & 0.91 BF Mag 192.98 1.74 123.99 1EL4 91.9 86 W T8 & 0.88 BF Elec 179.54 15.19 128.89 1EL4 93.0 86 W T8 & 0.81 BF Elec 190.54 4.18 129.35 1EL5 95.3 86 W T8 & 0.81 BF Elec 179.38 15.35 133.40 1

8B­69

EE-2006-STD-0131 COMMENT 37.2
Table 8B.44 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double Contact HO Syste

Industrial Sector with Low Lamp Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 157.21 0.00 14.23 0.00 

A: Lamp EL3 87.6 97 W T12 & 0.91 BF Mag 144.48 12.73 21.82 10.16 

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 144.86 12.35 22.19 10.16 

Event I: EL1 83.2 113 W T12 & 0.88 BF Elec 172.32 ­15.11 103.11 9.45 

Lamp Failure B: Lamp & EL3 87.6 97 W T12 & 0.91 BF Mag 170.21 ­13.00 99.67 10.16 

Ballast EL3 88.9 97 W T12 & 0.91 BF Mag 170.59 ­13.37 100.05 10.16 

Replacement EL3 88.9 97 W T12 & 0.9 BF Elec 161.57 ­4.35 104.14 15.34 

EL5 95.3 86 W T8 & 0.88 BF Elec 141.36 15.86 117.28 23.01 

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 149.37 0.00 14.23 0.00 

Event II:

Standards Lamp &

EL1 83.2 113 W T12 & 0.88 BF Elec 173.08 ­23.71 105.41 9.45 

EL3 87.6 97 W T12 & 0.91 BF Mag 170.98 ­21.60 101.98 10.16 

Induced

Retrofit

Ballast

Replacement

EL3 88.9 97 W T12 & 0.91 BF Mag 171.35 ­21.98 102.35 10.16 

EL3 88.9 97 W T12 & 0.9 BF Elec 162.33 ­12.96 106.45 15.34 EL5 95.3 86 W T8 & 0.88 BF Elec 142.12 7.25 119.59 23.01 

8B­70

EE-2006-STD-0131 COMMENT 37.2
Table 8B.44 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double Contact HO Syste

Industrial Sector with Low Lamp Prices (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 182.94 0.00 92.09 

EL1 83.2 113 W T12 & 0.88 BF Elec 172.32 10.62 103.11 

Event III: EL3 87.6 97 W T12 & 0.91 BF Mag 170.21 12.73 99.67 1

Ballast Failure Lamp & Ballast

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 170.59 12.35 100.05 1

EL3 88.9 97 W T12 & 0.9 BF Elec 161.57 21.37 104.14 1EL5 95.3 86 W T8 & 0.88 BF Elec 141.36 41.59 117.28 2

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 183.71 0.00 94.40 

EL1 83.2 113 W T12 & 0.88 BF Elec 173.08 10.62 105.41 

EL2 86.1 97 W T12 & 0.9 BF Elec 176.83 6.88 98.68 EL2 86.1 97 W T12 & 0.91 BF Mag 185.09 ­1.38 94.58 

Event V: New EL3 87.6 97 W T12 & 0.9 BF Elec 182.02 1.69 106.07 

Construction New Lamp & EL3 87.6 97 W T12 & 0.91 BF Mag 170.98 12.73 101.98 1

and Renovation Ballast

Purchase EL3 88.9 97 W T12 & 0.9 BF Elec 162.33 21.37 106.45 1

EL3 88.9 97 W T12 & 0.91 BF Mag 171.35 12.35 102.35 1EL4 91.9 86 W T8 & 0.88 BF Elec 171.63 12.07 117.65 1EL4 93.0 86 W T8 & 0.81 BF Elec 179.81 3.90 117.85 1EL5 95.3 86 W T8 & 0.81 BF Elec 167.47 16.24 119.59 1

8B­71

EE-2006-STD-0131 COMMENT 37.2
Table 8B.45 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double Contact HO Syste

Industrial Sector with No Ballast Prices

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC

Savings

$

Installed

Price

$

Operating

Cost

Savings

(Start Year

$

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 162.72 0.00 19.74 0.00 

A: Lamp EL3 87.6 97 W T12 & 0.91 BF Mag 155.05 7.67 32.38 10.16 

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 155.68 7.05 33.01 10.16 

Event I: EL1 83.2 113 W T12 & 0.88 BF Elec 155.36 7.36 31.28 9.45 

Lamp Failure B: Lamp & EL3 87.6 97 W T12 & 0.91 BF Mag 155.05 7.67 32.38 10.16 

Ballast EL3 88.9 97 W T12 & 0.91 BF Mag 155.68 7.05 33.01 10.16 

Replacement EL3 88.9 97 W T12 & 0.9 BF Elec 145.30 17.42 33.01 15.34 

EL5 95.3 86 W T8 & 0.88 BF Elec 112.86 49.87 23.23 23.01 

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 152.11 0.00 19.74 0.00 

Event II:

Standards Lamp &

EL1 83.2 113 W T12 & 0.88 BF Elec 155.36 ­3.25 31.28 9.45 

EL3 87.6 97 W T12 & 0.91 BF Mag 155.05 ­2.94 32.38 10.16 

Induced

Retrofit

Ballast

Replacement

EL3 88.9 97 W T12 & 0.91 BF Mag 155.68 ­3.56 33.01 10.16 

EL3 88.9 97 W T12 & 0.9 BF Elec 145.30 6.81 33.01 15.34 

EL5 95.3 86 W T8 & 0.88 BF Elec 112.86 39.26 23.23 23.01 

8B­72

EE-2006-STD-0131 COMMENT 37.2
Table 8B.45 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double Contact HO Syste

Industrial Sector with No Ballast Prices (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 162.72 0.00 19.74 

EL1 83.2 113 W T12 & 0.88 BF Elec 155.36 7.36 31.28 

Event III: EL3 87.6 97 W T12 & 0.91 BF Mag 155.05 7.67 32.38 1

Ballast Failure Lamp & Ballast

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 155.68 7.05 33.01 1

EL3 88.9 97 W T12 & 0.9 BF Elec 145.30 17.42 33.01 1EL5 95.3 86 W T8 & 0.88 BF Elec 112.86 49.87 23.23 2

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 162.72 0.00 19.74 

EL1 83.2 113 W T12 & 0.88 BF Elec 155.36 7.36 31.28 

EL2 86.1 97 W T12 & 0.9 BF Elec 151.42 11.31 20.06 EL2 86.1 97 W T12 & 0.91 BF Mag 161.49 1.23 20.06 

Event V: New EL3 87.6 97 W T12 & 0.9 BF Elec 162.60 0.13 32.38 

Construction New Lamp & EL3 87.6 97 W T12 & 0.91 BF Mag 155.05 7.67 32.38 1

and Renovation Ballast

Purchase EL3 88.9 97 W T12 & 0.9 BF Elec 145.30 17.42 33.01 1

EL3 88.9 97 W T12 & 0.91 BF Mag 155.68 7.05 33.01 1EL4 91.9 86 W T8 & 0.88 BF Elec 133.32 29.40 20.01 1EL4 93.0 86 W T8 & 0.81 BF Elec 139.90 22.82 20.34 1EL5 95.3 86 W T8 & 0.81 BF Elec 131.63 31.09 23.23 1

8B­73

EE-2006-STD-0131 COMMENT 37.2
Table 8B.46 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double Contact HO System 

Industrial Sector with High Lamp Prices

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 139.77 0.00 17.10 

EL2 86.1 97 W T12 & 0.89 BF Elec 162.48 ­22.71 107.64 

Event I: Lamp

Failure

B: Lamp &

EL3 87.6 97 W T12 & 0.88 BF Elec 177.15 ­37.38 124.90 

EL3 88.9 97 W T12 & 0.88 BF Elec 178.02 ­38.26 125.77 

Replacement

Ballast

EL4 91.9 86 W T8 & 0.88 BF Elec 144.21 ­4.44 126.58 1

EL4 93.0 86 W T8 & 0.88 BF Elec 148.23 ­8.46 127.04 1EL5 95.3 86 W T8 & 0.81 BF Elec 145.70 ­5.93 131.09 1

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 130.48 0.00 17.10 

EL2 86.1 97 W T12 & 0.89 BF Elec 163.24 ­32.76 109.95 

Event II: EL3 87.6 97 W T12 & 0.88 BF Elec 177.91 ­47.43 127.21 

Standards Lamp & Ballast EL3 88.9 97 W T12 & 0.88 BF Elec 178.79 ­48.30 128.08 

Induced Retrofit Replacement EL4 91.9 86 W T8 & 0.88 BF Elec 144.97 ­14.48 128.89 1

EL4 93.0 86 W T8 & 0.88 BF Elec 148.99 ­18.51 129.35 1EL5 95.3 86 W T8 & 0.81 BF Elec 146.46 ­15.98 133.40 1

8B­74

EE-2006-STD-0131 COMMENT 37.2
Table 8B.46 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double Contact HO System 

Industrial Sector with High Lamp Prices (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 165.50 0.00 94.95 

EL2 86.1 97 W T12 & 0.89 BF Elec 162.48 3.01 107.64 

Event III:

Ballast Failure Lamp & Ballast

EL3 87.6 97 W T12 & 0.88 BF Elec 177.15 ­11.65 124.90 

EL3 88.9 97 W T12 & 0.88 BF Elec 178.02 ­12.53 125.77 

Replacement EL4 91.9 86 W T8 & 0.88 BF Elec 144.21 21.29 126.58 1

EL4 93.0 86 W T8 & 0.88 BF Elec 148.23 17.27 127.04 1EL5 95.3 86 W T8 & 0.81 BF Elec 145.70 19.79 131.09 1

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 166.26 0.00 97.26 

EL2 86.1 97 W T12 & 0.89 BF Elec 163.24 3.01 109.95 

Event V: New EL3 87.6 97 W T12 & 0.88 BF Elec 177.91 ­11.65 127.21 

Construction New Lamp & EL3 88.9 97 W T12 & 0.88 BF Elec 178.79 ­12.53 128.08 

and Renovation Ballast

Purchase EL4 91.9 86 W T8 & 0.88 BF Elec 144.97 21.29 128.89 1

EL4 93.0 86 W T8 & 0.88 BF Elec 148.99 17.27 129.35 1EL5 95.3 86 W T8 & 0.81 BF Elec 146.46 19.79 133.40 1

8B­75

EE-2006-STD-0131 COMMENT 37.2
Table 8B.47 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double Contact HO System 

Industrial Sector with Low Lamp Prices

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 133.41 0.00 10.74 

EL2 86.1 97 W T12 & 0.89 BF Elec 151.21 ­17.80 96.37 

Event I: Lamp

Failure

B: Lamp &

EL3 87.6 97 W T12 & 0.88 BF Elec 156.02 ­22.61 103.77 

EL3 88.9 97 W T12 & 0.88 BF Elec 156.39 ­22.98 104.14 

Replacement

Ballast

EL4 91.9 86 W T8 & 0.88 BF Elec 137.82 ­4.42 115.35 1

EL4 93.0 86 W T8 & 0.88 BF Elec 140.14 ­6.73 115.54 1EL5 95.3 86 W T8 & 0.81 BF Elec 135.98 ­2.57 117.28 1

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 127.32 0.00 10.74 

EL2 86.1 97 W T12 & 0.89 BF Elec 151.97 ­24.65 98.68 

Event II: EL3 87.6 97 W T12 & 0.88 BF Elec 156.78 ­29.46 106.07 

Standards Lamp & Ballast EL3 88.9 97 W T12 & 0.88 BF Elec 157.15 ­29.83 106.45 

Induced Retrofit Replacement EL4 91.9 86 W T8 & 0.88 BF Elec 138.59 ­11.27 117.65 1

EL4 93.0 86 W T8 & 0.88 BF Elec 140.90 ­13.58 117.85 1EL5 95.3 86 W T8 & 0.81 BF Elec 136.74 ­9.42 119.59 1

8B­76

EE-2006-STD-0131 COMMENT 37.2
Table 8B.47 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double Contact HO System 

Industrial Sector with Low Lamp Prices (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 159.14 0.00 88.59 

EL2 86.1 97 W T12 & 0.89 BF Elec 151.21 7.92 96.37 

Event III:

Ballast Failure Lamp & Ballast

EL3 87.6 97 W T12 & 0.88 BF Elec 156.02 3.12 103.77 

EL3 88.9 97 W T12 & 0.88 BF Elec 156.39 2.74 104.14 

Replacement EL4 91.9 86 W T8 & 0.88 BF Elec 137.82 21.31 115.35 1

EL4 93.0 86 W T8 & 0.88 BF Elec 140.14 19.00 115.54 1EL5 95.3 86 W T8 & 0.81 BF Elec 135.98 23.16 117.28 1

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 159.90 0.00 90.90 

EL2 86.1 97 W T12 & 0.89 BF Elec 151.97 7.92 98.68 

Event V: New EL3 87.6 97 W T12 & 0.88 BF Elec 156.78 3.12 106.07 

Construction New Lamp & EL3 88.9 97 W T12 & 0.88 BF Elec 157.15 2.74 106.45 

and Renovation Ballast

Purchase EL4 91.9 86 W T8 & 0.88 BF Elec 138.59 21.31 117.65 1

EL4 93.0 86 W T8 & 0.88 BF Elec 140.90 19.00 117.85 1EL5 95.3 86 W T8 & 0.81 BF Elec 136.74 23.16 119.59 1

8B­77

EE-2006-STD-0131 COMMENT 37.2
Table 8B.48 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double Contact HO System 

Industrial Sector with No Ballast Prices

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 136.59 0.00 13.92 

EL2 86.1 97 W T12 & 0.89 BF Elec 129.76 6.82 20.06 

Event I: Lamp

Failure

B: Lamp &

EL3 87.6 97 W T12 & 0.88 BF Elec 139.50 ­2.91 32.38 

EL3 88.9 97 W T12 & 0.88 BF Elec 140.13 ­3.54 33.01 

Replacement

Ballast

EL4 91.9 86 W T8 & 0.88 BF Elec 107.65 28.93 20.01 1

EL4 93.0 86 W T8 & 0.88 BF Elec 110.82 25.77 20.34 1EL5 95.3 86 W T8 & 0.81 BF Elec 107.48 29.11 23.23 1

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 128.90 0.00 13.92 

EL2 86.1 97 W T12 & 0.89 BF Elec 129.76 ­0.86 20.06 

Event II: EL3 87.6 97 W T12 & 0.88 BF Elec 139.50 ­10.60 32.38 

Standards Lamp & Ballast EL3 88.9 97 W T12 & 0.88 BF Elec 140.13 ­11.22 33.01 

Induced Retrofit Replacement EL4 91.9 86 W T8 & 0.88 BF Elec 107.65 21.25 20.01 1

EL4 93.0 86 W T8 & 0.88 BF Elec 110.82 18.08 20.34 1EL5 95.3 86 W T8 & 0.81 BF Elec 107.48 21.42 23.23 1

8B­78

EE-2006-STD-0131 COMMENT 37.2
Table 8B.48 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double Contact HO System 

Industrial Sector with No Ballast Prices (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 136.59 0.00 13.92 

EL2 86.1 97 W T12 & 0.89 BF Elec 129.76 6.82 20.06 

Event III:

Ballast Failure Lamp & Ballast

EL3 87.6 97 W T12 & 0.88 BF Elec 139.50 ­2.91 32.38 

EL3 88.9 97 W T12 & 0.88 BF Elec 140.13 ­3.54 33.01 

Replacement EL4 91.9 86 W T8 & 0.88 BF Elec 107.65 28.93 20.01 1

EL4 93.0 86 W T8 & 0.88 BF Elec 110.82 25.77 20.34 1EL5 95.3 86 W T8 & 0.81 BF Elec 107.48 29.11 23.23 1

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 136.59 0.00 13.92 

EL2 86.1 97 W T12 & 0.89 BF Elec 129.76 6.82 20.06 

Event V: New EL3 87.6 97 W T12 & 0.88 BF Elec 139.50 ­2.91 32.38 

Construction New Lamp & EL3 88.9 97 W T12 & 0.88 BF Elec 140.13 ­3.54 33.01 

and Renovation Ballast

Purchase EL4 91.9 86 W T8 & 0.88 BF Elec 107.65 28.93 20.01 1

EL4 93.0 86 W T8 & 0.88 BF Elec 110.82 25.77 20.34 1EL5 95.3 86 W T8 & 0.81 BF Elec 107.48 29.11 23.23 1

8B­79

EE-2006-STD-0131 COMMENT 37.2
8B.7.3 Electricity Price Trend Case Results

Finally, DOE analyzed the impacts of high and low growth trends for future electricity

prices, as lamp and lamp­and­ballast system operating costs are directly related to future

electricity prices. Specifically, DOE examined the impacts of using the AEO2008 high and low

growth price trend cases instead of the reference case electricity prices. Chapter 8 describes and

compares the three price trends. The following tables present LCC savings and PBP results

using the low and high growth cases.

8B.7.3.1 Product Class: 4­foot medium bipin ≤ 4,500K

The following tables present the findings of an LCC analysis on the three 4­foot medium

bipin GSFL baselines operating in the commercial sector with a CCT less than or equal to

4,500K, considering AEO2008 high and low growth price trend cases. Key inputs consist of

using medium lamp and ballast prices and an analysis period of 5.5 yrs. Note: Lamp

replacement results in Event I are not shown for a 34W T12 lamp because there are no energy

saving lamp replacement options.

8B­80

EE-2006-STD-0131 COMMENT 37.2
Table 8B.49 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector under the AEO2008 High Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 78.0 41 W T12 & 0.95 BF Mag 207.76 0.00 13.96 

A: Lamp

Replacement EL3 91.2 34 W T12 & 0.88 BF Mag 184.58 23.18 25.13 

EL1 80.5 41 W T12 & 0.88 BF Elec 213.09 ­5.33 72.51 EL1 82.9 41 W T12 & 0.87 BF Elec 213.78 ­6.03 77.16 EL2 86.2 32.5 W T8 & 1.18 BF Elec 213.69 ­5.93 65.11 

Event I: Lamp

Failure B: Lamp &

Ballast

Replacement

EL2 87.8 41 W T12 & 0.87 BF Elec 214.05 ­6.29 77.45 

EL3 91.2 34 W T12 & 0.88 BF Elec 190.78 16.98 77.06 1EL3 90.8 32.5 W T8 & 1 BF Elec 192.96 14.80 68.21 1EL4 92.3 32.5 W T8 & 0.88 BF Elec 171.11 36.65 60.96 1EL4 93.8 30.4 W T8 & 1 BF Elec 183.61 24.15 69.49 1EL4 93.0 26.6 W T8 & 1.18 BF Elec 178.87 28.88 73.25 1EL5 95.4 32.5 W T8 & 0.88 BF Elec 172.50 35.26 62.52 1EL5 96.0 28.4 W T8 & 1 BF Elec 176.60 31.16 68.89 1

8B­81

EE-2006-STD-0131 COMMENT 37.2
Table 8B.49 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector under the AEO2008 High Growth Electricity Price Trend Case (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 78.0 41 W T12 & 0.95 BF Mag 200.94 0.00 13.96 

EL1 80.5 41 W T12 & 0.88 BF Elec 214.45 ­13.52 74.82 

EL1 82.9 41 W T12 & 0.87 BF Elec 215.15 ­14.21 79.46 EL2 86.2 32.5 W T8 & 1.18 BF Elec 215.05 ­14.11 67.42 EL2 87.8 41 W T12 & 0.87 BF Elec 215.41 ­14.47 79.76 

Event II:

Standards

Induced Retrofit

Lamp & Ballast

Replacement

EL3 91.2 34 W T12 & 0.88 BF Elec 192.14 8.80 79.37 1

EL3 90.8 32.5 W T8 & 1 BF Elec 194.32 6.62 70.52 1EL4 92.3 32.5 W T8 & 0.88 BF Elec 172.47 28.47 63.26 1EL4 93.8 30.4 W T8 & 1 BF Elec 184.97 15.97 71.80 1EL4 93.0 26.6 W T8 & 1.18 BF Elec 180.24 20.70 75.56 1EL5 95.4 32.5 W T8 & 0.88 BF Elec 173.86 27.08 64.83 1EL5 96.0 28.4 W T8 & 1 BF Elec 177.97 22.97 71.19 1

Baseline Baseline 78.0 41 W T12 & 0.88 BF Elec 206.47 0.00 65.89 

EL1 80.5 41 W T12 & 0.87 BF Elec 212.08 ­5.60 72.51 

EL1 82.9 41 W T12 & 0.87 BF Elec 213.78 ­7.31 77.16 EL2 87.8 41 W T12 & 0.87 BF Elec 214.05 ­7.57 77.45 

Event III:

Ballast Failure Lamp & Ballast

Replacement

EL3 91.2 34 W T12 & 0.88 BF Elec 190.78 15.70 77.06 

EL3 90.8 32.5 W T8 & 1 BF Elec 192.96 13.52 68.21 EL4 92.3 32.5 W T8 & 0.88 BF Elec 171.11 35.37 60.96 EL4 93.8 30.4 W T8 & 1 BF Elec 183.61 22.86 69.49 EL4 93.0 26.6 W T8 & 1.18 BF Elec 178.87 27.60 73.25 EL5 95.4 32.5 W T8 & 0.88 BF Elec 172.50 33.98 62.52 EL5 96.0 28.4 W T8 & 1 BF Elec 176.60 29.87 68.89 

* Comparative lumens are sometimes non­zero for baseline T12 electronic systems under events III and IV (ballast failure and retro

package is compared to a system with a T12 magnetic ballast. DOE chose to compare these systems for these events because it recog

regulations will prohibit the use of magnetic ballasts, future purchasers may still seek the current lumen package delivered by curren

8B­82

EE-2006-STD-0131 COMMENT 37.2
Table 8B.49 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector under the AEO2008 High Growth Electricity Price Trend Case (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL2 86.2 32.5 W T8 & 1.18 BF Elec 215.05 0.00 67.42 

EL3 91.2 34 W T12 & 0.88 BF Elec 192.14 22.91 79.37 

EL3 90.8 32.5 W T8 & 1 BF Elec 194.32 20.73 70.52 

Event IV: EL4 92.3 32.5 W T8 & 0.88 BF Elec 172.47 42.58 63.26 

Ballast Retrofit Lamp & Ballast

Replacement EL4 93.8 30.4 W T8 & 1 BF Elec 184.97 30.08 71.80 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 180.24 34.81 75.56 EL5 95.4 32.5 W T8 & 0.88 BF Elec 173.86 41.19 64.83 EL5 96.0 28.4 W T8 & 1 BF Elec 177.97 37.08 71.19 1

8B­83

EE-2006-STD-0131 COMMENT 37.2
Table 8B.50 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector under the AEO2008 Low Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 78.0 41 W T12 & 0.95 BF Mag 197.28 0.00 13.96 

A: Lamp

Replacement EL3 91.2 34 W T12 & 0.88 BF Mag 175.80 21.47 25.13 

EL1 80.5 41 W T12 & 0.88 BF Elec 204.34 ­7.07 72.51 EL1 82.9 41 W T12 & 0.87 BF Elec 205.09 ­7.82 77.16 EL2 86.2 32.5 W T8 & 1.18 BF Elec 204.48 ­7.20 65.11 

Event I: Lamp

Failure B: Lamp &

Ballast

Replacement

EL2 87.8 41 W T12 & 0.87 BF Elec 205.36 ­8.08 77.45 

EL3 91.2 34 W T12 & 0.88 BF Elec 183.33 13.95 77.06 1EL3 90.8 32.5 W T8 & 1 BF Elec 185.04 12.23 68.21 1EL4 92.3 32.5 W T8 & 0.88 BF Elec 164.05 33.22 60.96 1EL4 93.8 30.4 W T8 & 1 BF Elec 176.27 21.00 69.49 1EL4 93.0 26.6 W T8 & 1.18 BF Elec 171.74 25.53 73.25 1EL5 95.4 32.5 W T8 & 0.88 BF Elec 165.44 31.83 62.52 1EL5 96.0 28.4 W T8 & 1 BF Elec 169.78 27.50 68.89 1

8B­84

EE-2006-STD-0131 COMMENT 37.2
Table 8B.50 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector under the AEO2008 Low Growth Electricity Price Trend Case (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 78.0 41 W T12 & 0.95 BF Mag 190.46 0.00 13.96 

EL1 80.5 41 W T12 & 0.88 BF Elec 205.71 ­15.25 74.82 

EL1 82.9 41 W T12 & 0.87 BF Elec 206.45 ­16.00 79.46 EL2 86.2 32.5 W T8 & 1.18 BF Elec 205.84 ­15.38 67.42 

EL2 87.8 41 W T12 & 0.87 BF Elec 206.72 ­16.26 79.76 

Event II:

Standards

Induced Retrofit

Lamp & Ballast

Replacement

EL3 91.2 34 W T12 & 0.88 BF Elec 184.69 5.76 79.37 1

EL3 90.8 32.5 W T8 & 1 BF Elec 186.41 4.05 70.52 1EL4 92.3 32.5 W T8 & 0.88 BF Elec 165.42 25.04 63.26 1EL4 93.8 30.4 W T8 & 1 BF Elec 177.64 12.82 71.80 1EL4 93.0 26.6 W T8 & 1.18 BF Elec 173.11 17.35 75.56 1EL5 95.4 32.5 W T8 & 0.88 BF Elec 166.81 23.65 64.83 1EL5 96.0 28.4 W T8 & 1 BF Elec 171.14 19.32 71.19 1

Baseline Baseline 78.0 41 W T12 & 0.88 BF Elec 197.73 0.00 65.89 

EL1 80.5 41 W T12 & 0.87 BF Elec 203.38 ­5.66 72.51 

EL1 82.9 41 W T12 & 0.87 BF Elec 205.09 ­7.37 77.16 EL2 87.8 41 W T12 & 0.87 BF Elec 205.36 ­7.63 77.45 

Event III:

Ballast Failure Lamp & Ballast

Replacement

EL3 91.2 34 W T12 & 0.88 BF Elec 183.33 14.40 77.06 

EL3 90.8 32.5 W T8 & 1 BF Elec 185.04 12.68 68.21 EL4 92.3 32.5 W T8 & 0.88 BF Elec 164.05 33.67 60.96 EL4 93.8 30.4 W T8 & 1 BF Elec 176.27 21.45 69.49 EL4 93.0 26.6 W T8 & 1.18 BF Elec 171.74 25.98 73.25 EL5 95.4 32.5 W T8 & 0.88 BF Elec 165.44 32.28 62.52 EL5 96.0 28.4 W T8 & 1 BF Elec 169.78 27.95 68.89 

* Comparative lumens are sometimes non­zero for baseline T12 electronic systems under events III and IV (ballast failure and retrofit) 

package is compared to a system with a T12 magnetic ballast. DOE chose to compare these systems for these events because it recogn

regulations will prohibit the use of magnetic ballasts, future purchasers may still seek the current lumen package delivered by current T

8B­85

EE-2006-STD-0131 COMMENT 37.2
Table 8B.50 LCC and PBP Results for a Three­Lamp 4­Foot 40W T12 Medium Bipin System Operating i

Sector under the AEO2008 Low Growth Electricity Price Trend Case (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL2 86.2 32.5 W T8 & 1.18 BF Elec 205.84 0.00 67.42 

EL3 91.2 34 W T12 & 0.88 BF Elec 184.69 21.15 79.37 

EL3 90.8 32.5 W T8 & 1 BF Elec 186.41 19.43 70.52 

Event IV: EL4 92.3 32.5 W T8 & 0.88 BF Elec 165.42 40.42 63.26 

Ballast Retrofit Lamp & Ballast

Replacement EL4 93.8 30.4 W T8 & 1 BF Elec 177.64 28.20 71.80 

EL4 93.0 26.6 W T8 & 1.18 BF Elec 173.11 32.73 75.56 EL5 95.4 32.5 W T8 & 0.88 BF Elec 166.81 39.03 64.83 EL5 96.0 28.4 W T8 & 1 BF Elec 171.14 34.70 71.19 

8B­86

EE-2006-STD-0131 COMMENT 37.2
Table 8B.51 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin System Operating i

Sector under the AEO2008 High Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 77.9 34 W T12 & 0.88 BF Mag 173.60 0.00 11.22 

EL1 82.4 34 W T12 & 0.88 BF Elec 183.48 ­9.89 66.84 

EL2 85.3 34 W T12 & 0.86 BF Elec 188.48 ­14.88 73.87 

EL2 86.2 32.5 W T8 & 0.88 BF Elec 169.43 4.17 57.43 

Event I: Lamp

Failure

B: Lamp &

EL3 90.8 32.5 W T8 & 0.78 BF Elec 159.29 14.30 60.53 1

EL3 91.2 34 W T12 & 0.86 BF Elec 188.75 ­15.15 77.06 

Ballast

Replacement EL4 92.3 32.5 W T8 & 0.75 BF Elec 153.89 19.70 60.96 1

EL4 93.8 30.4 W T8 & 0.78 BF Elec 151.92 21.68 61.81 1EL4 93.0 26.6 W T8 & 0.88 BF Elec 142.56 31.03 65.57 1EL5 95.4 32.5 W T8 & 0.71 BF Elec 149.99 23.61 62.52 1EL5 96.0 28.4 W T8 & 0.78 BF Elec 146.69 26.91 61.20 1

Baseline Baseline 77.9 34 W T12 & 0.88 BF Mag 168.04 0.00 11.22 

EL1 82.4 34 W T12 & 0.88 BF Elec 184.85 ­16.81 69.15 

EL2 85.3 34 W T12 & 0.86 BF Elec 189.84 ­21.80 76.18 

EL2 86.2 32.5 W T8 & 0.88 BF Elec 170.79 ­2.75 59.74 

Event II: EL3 90.8 32.5 W T8 & 0.78 BF Elec 160.66 7.38 62.84 1

Standards Lamp & Ballast EL3 91.2 34 W T12 & 0.86 BF Elec 190.11 ­22.07 79.37 

Induced Retrofit Replacement EL4 92.3 32.5 W T8 & 0.75 BF Elec 155.26 12.78 63.26 1

EL4 93.8 30.4 W T8 & 0.78 BF Elec 153.28 14.75 64.11 1EL4 93.0 26.6 W T8 & 0.88 BF Elec 143.93 24.11 67.88 1EL5 95.4 32.5 W T8 & 0.71 BF Elec 151.35 16.69 64.83 1EL5 96.0 28.4 W T8 & 0.78 BF Elec 148.05 19.98 63.51 1

8B­87

EE-2006-STD-0131 COMMENT 37.2
Table 8B.51 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin System Operating i

Sector under the AEO2008 High Growth Electricity Price Trend Case (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 77.9 34 W T12 & 0.88 BF Elec 179.79 0.00 63.15 

EL1 82.4 34 W T12 & 0.86 BF Elec 181.45 ­1.66 66.84 

EL2 85.3 34 W T12 & 0.86 BF Elec 188.48 ­8.68 73.87 

EL2 86.2 32.5 W T8 & 0.88 BF Elec 169.43 10.36 57.43 

Event III:

Ballast Failure Lamp & Ballast

EL3 90.8 32.5 W T8 & 0.78 BF Elec 159.29 20.50 60.53 

EL3 91.2 34 W T12 & 0.86 BF Elec 188.75 ­8.95 77.06 

Replacement EL4 92.3 32.5 W T8 & 0.75 BF Elec 153.89 25.90 60.96 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 151.92 27.87 61.81 EL4 93.0 26.6 W T8 & 0.88 BF Elec 142.56 37.23 65.57 EL5 95.4 32.5 W T8 & 0.71 BF Elec 149.99 29.81 62.52 EL5 96.0 28.4 W T8 & 0.78 BF Elec 146.69 33.10 61.20 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 170.79 0.00 59.74 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 160.66 19.14 62.84 

Event IV:

Ballast Retrofit Lamp & Ballast

Replacement

EL4 92.3 32.5 W T8 & 0.75 BF Elec 155.26 24.54 63.26 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 153.28 26.51 64.11 EL4 93.0 26.6 W T8 & 0.88 BF Elec 143.93 35.87 67.88 EL5 95.4 32.5 W T8 & 0.71 BF Elec 151.35 28.44 64.83 EL5 96.0 28.4 W T8 & 0.78 BF Elec 148.05 31.74 63.51 

8B­88

EE-2006-STD-0131 COMMENT 37.2
Table 8B.52 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin System Operating i

Sector under the AEO2008 Low Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 77.9 34 W T12 & 0.88 BF Mag 164.82 0.00 11.22 

EL1 82.4 34 W T12 & 0.88 BF Elec 176.04 ­11.21 66.84 

EL2 85.3 34 W T12 & 0.86 BF Elec 181.14 ­16.32 73.87 

EL2 86.2 32.5 W T8 & 0.88 BF Elec 162.38 2.44 57.43 

Event I: Lamp

Failure

B: Lamp &

EL3 90.8 32.5 W T8 & 0.78 BF Elec 152.96 11.86 60.53 

EL3 91.2 34 W T12 & 0.86 BF Elec 181.41 ­16.59 77.06 

Ballast

Replacement EL4 92.3 32.5 W T8 & 0.75 BF Elec 147.78 17.04 60.96 1

EL4 93.8 30.4 W T8 & 0.78 BF Elec 146.06 18.76 61.81 1EL4 93.0 26.6 W T8 & 0.88 BF Elec 137.16 27.66 65.57 1EL5 95.4 32.5 W T8 & 0.71 BF Elec 144.16 20.66 62.52 1EL5 96.0 28.4 W T8 & 0.78 BF Elec 141.24 23.58 61.20 1

Baseline Baseline 77.9 34 W T12 & 0.88 BF Mag 159.26 0.00 11.22 

EL1 82.4 34 W T12 & 0.88 BF Elec 177.40 ­18.14 69.15 

EL2 85.3 34 W T12 & 0.86 BF Elec 182.50 ­23.24 76.18 

EL2 86.2 32.5 W T8 & 0.88 BF Elec 163.74 ­4.48 59.74 

Event II: EL3 90.8 32.5 W T8 & 0.78 BF Elec 154.32 4.94 62.84 

Standards Lamp & Ballast EL3 91.2 34 W T12 & 0.86 BF Elec 182.77 ­23.51 79.37 

Induced Retrofit Replacement EL4 92.3 32.5 W T8 & 0.75 BF Elec 149.14 10.12 63.26 1

EL4 93.8 30.4 W T8 & 0.78 BF Elec 147.42 11.84 64.11 1EL4 93.0 26.6 W T8 & 0.88 BF Elec 138.52 20.74 67.88 1EL5 95.4 32.5 W T8 & 0.71 BF Elec 145.52 13.74 64.83 1EL5 96.0 28.4 W T8 & 0.78 BF Elec 142.61 16.66 63.51 1

8B­89

EE-2006-STD-0131 COMMENT 37.2
Table 8B.17 LCC and PBP Results for a Three­Lamp 4­Foot 34W T12 Medium Bipin System Operating i

Sector with Low Lamp Prices (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 77.9 34 W T12 & 0.88 BF Elec 172.35 0.00 63.15 

EL1 82.4 34 W T12 & 0.86 BF Elec 174.11 ­1.77 66.84 

EL2 85.3 34 W T12 & 0.86 BF Elec 181.14 ­8.79 73.87 

EL2 86.2 32.5 W T8 & 0.88 BF Elec 162.38 9.97 57.43 

Event III:

Ballast Failure Lamp & Ballast

EL3 90.8 32.5 W T8 & 0.78 BF Elec 152.96 19.38 60.53 

EL3 91.2 34 W T12 & 0.86 BF Elec 181.41 ­9.06 77.06 

Replacement EL4 92.3 32.5 W T8 & 0.75 BF Elec 147.78 24.57 60.96 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 146.06 26.29 61.81 EL4 93.0 26.6 W T8 & 0.88 BF Elec 137.16 35.19 65.57 EL5 95.4 32.5 W T8 & 0.71 BF Elec 144.16 28.19 62.52 EL5 96.0 28.4 W T8 & 0.78 BF Elec 141.24 31.10 61.20 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 163.74 0.00 59.74 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 154.32 18.02 62.84 

Event IV:

Ballast Retrofit Lamp & Ballast

Replacement

EL4 92.3 32.5 W T8 & 0.75 BF Elec 149.14 23.21 63.26 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 147.42 24.92 64.11 EL4 93.0 26.6 W T8 & 0.88 BF Elec 138.52 33.82 67.88 EL5 95.4 32.5 W T8 & 0.71 BF Elec 145.52 26.83 64.83 EL5 96.0 28.4 W T8 & 0.78 BF Elec 142.61 29.74 63.51 

8B­90

EE-2006-STD-0131 COMMENT 37.2
Table 8B.53 LCC and PBP Results for a Three­Lamp 4­Foot 32W T8 Medium Bipin System Operating in 

Sector under the AEO2008 High Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 142.60 0.00 11.97 

Event I: Lamp EL4 93.8 30.4 W T8 & 0.88 BF Elec 137.43 5.17 16.35 

Failure A: Lamp

Replacement EL4 93.0 26.6 W T8 & 0.88 BF Elec 115.73 26.87 20.11 

EL5 96.0 28.4 W T8 & 0.88 BF Elec 131.39 11.20 15.74 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 169.43 0.00 57.43 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 159.29 10.14 60.53 

Event III:

Ballast Failure Lamp & Ballast

EL4 92.3 32.5 W T8 & 0.75 BF Elec 153.89 15.54 60.96 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 151.92 17.51 61.81 

Replacement EL4 93.0 26.6 W T8 & 0.88 BF Elec 142.56 26.87 65.57 

EL5 95.4 32.5 W T8 & 0.75 BF Elec 155.28 14.15 62.52 EL5 96.0 28.4 W T8 & 0.88 BF Elec 158.23 11.20 61.20 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 170.79 0.00 59.74 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 160.66 10.14 62.84 

Event V: New EL4 92.3 32.5 W T8 & 0.75 BF Elec 155.26 15.54 63.26 

Construction New Lamp & EL4 93.8 30.4 W T8 & 0.78 BF Elec 153.28 17.51 64.11 

and Renovation Ballast

Purchase EL4 93.0 26.6 W T8 & 0.88 BF Elec 143.93 26.87 67.88 

EL5 95.4 32.5 W T8 & 0.75 BF Elec 156.65 14.15 64.83 EL5 96.0 28.4 W T8 & 0.88 BF Elec 159.59 11.20 63.51 

8B­91

EE-2006-STD-0131 COMMENT 37.2
Table 8B.54 LCC and PBP Results for a Three­Lamp 4­Foot 32W T8 Medium Bipin System Operating in 

Sector under the AEO2008 Low Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 135.54 0.00 11.97 

Event I: Lamp EL4 93.8 30.4 W T8 & 0.88 BF Elec 130.90 4.65 16.35 

Failure A: Lamp

Replacement EL4 93.0 26.6 W T8 & 0.88 BF Elec 110.32 25.22 20.11 

EL5 96.0 28.4 W T8 & 0.88 BF Elec 125.32 10.23 15.74 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 162.38 0.00 57.43 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 152.96 9.42 60.53 

Event III:

Ballast Failure Lamp & Ballast

EL4 92.3 32.5 W T8 & 0.75 BF Elec 147.78 14.60 60.96 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 146.06 16.32 61.81 

Replacement EL4 93.0 26.6 W T8 & 0.88 BF Elec 137.16 25.22 65.57 

EL5 95.4 32.5 W T8 & 0.75 BF Elec 149.17 13.21 62.52 EL5 96.0 28.4 W T8 & 0.88 BF Elec 152.15 10.23 61.20 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 163.74 0.00 59.74 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 154.32 9.42 62.84 

Event V: New EL4 92.3 32.5 W T8 & 0.75 BF Elec 149.14 14.60 63.26 

Construction New Lamp & EL4 93.8 30.4 W T8 & 0.78 BF Elec 147.42 16.32 64.11 

and Renovation Ballast

Purchase EL4 93.0 26.6 W T8 & 0.88 BF Elec 138.52 25.22 67.88 

EL5 95.4 32.5 W T8 & 0.75 BF Elec 150.53 13.21 64.83 EL5 96.0 28.4 W T8 & 0.88 BF Elec 153.51 10.23 63.51 

For the 4­foot medium bipin product class with CCT less than or equal to 4,500K in the residential sector

baseline lamp: a 40W T12. The following tables present the LCC savings and PBP results for this 4­foot mediu

operating in the residential sector under the AEO2008 high and low growth electricity price trend cases. Key inp

medium lamp and ballast prices. For the lamp failure event, residential high operating hours (of 1,210 hours per 

the analysis period is 2.5 years. For other events, residential average operating hours (of 789 hours per year) wer

analysis period is 15 years.

8B­92

EE-2006-STD-0131 COMMENT 37.2
Table 8B.55 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin System Operating in 

Sector under the AEO2008 High Growth Electricity Price Trend Case and Average Operating Hours

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 76.8 41 W T12 & 0.68 BF Mag 112.25 0.00 49.47 

EL1 80.5 41 W T12 & 0.65 BF Elec 103.02 9.23 51.00 

EL1 82.4 34 W T12 & 0.85 BF Elec 102.83 9.42 47.22 EL1 82.9 41 W T12 & 0.65 BF Elec 106.11 6.13 54.10 EL2 85.3 34 W T12 & 0.75 BF Elec 94.95 17.29 51.90 EL2 86.2 32.5 W T8 & 0.78 BF Elec 94.96 17.29 48.64 

Event III:

Ballast Failure Lamp & Ballast

EL2 87.8 41 W T12 & 0.65 BF Elec 106.31 5.93 54.29 

EL3 91.2 34 W T12 & 0.66 BF Mag 111.76 0.49 57.95 

Replacement EL3 91.2 34 W T12 & 0.75 BF Elec 97.08 15.16 54.03 

EL3 90.8 32.5 W T8 & 0.75 BF Elec 95.17 17.08 50.71 EL4 92.3 32.5 W T8 & 0.75 BF Elec 95.45 16.79 50.99 EL4 93.8 30.4 W T8 & 0.75 BF Elec 93.89 18.36 51.56 EL4 93.0 26.6 W T8 & 0.78 BF Elec 90.36 21.89 54.07 EL5 95.4 32.5 W T8 & 0.71 BF Elec 94.02 18.23 52.03 EL5 96.0 28.4 W T8 & 0.78 BF Elec 92.05 20.20 51.16 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 103.46 0.00 50.95 

EL3 91.2 34 W T12 & 0.75 BF Elec 99.39 4.07 56.34 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 99.34 4.13 53.02 

Event V: New

Construction

and Renovation

New Lamp &

Ballast

Purchase

EL4 92.3 32.5 W T8 & 0.78 BF Elec 99.62 3.84 53.30 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 97.73 5.73 53.87 

EL4 93.0 26.6 W T8 & 0.88 BF Elec 97.08 6.38 56.37 EL5 95.4 32.5 W T8 & 0.75 BF Elec 98.80 4.66 54.34 EL5 96.0 28.4 W T8 & 0.78 BF Elec 94.36 9.10 53.46 

8B­93

EE-2006-STD-0131 COMMENT 37.2
Table 8B.56 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin System Operating in 

Sector under the AEO2008 Low Growth Electricity Price Trend Case and Average Operating Hours

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 76.8 41 W T12 & 0.68 BF Mag 109.00 0.00 49.47 

EL1 80.5 41 W T12 & 0.65 BF Elec 100.33 8.67 51.00 

EL1 82.4 34 W T12 & 0.85 BF Elec 99.95 9.05 47.22 EL1 82.9 41 W T12 & 0.65 BF Elec 103.42 5.57 54.10 EL2 85.3 34 W T12 & 0.75 BF Elec 92.73 16.27 51.90 EL2 86.2 32.5 W T8 & 0.78 BF Elec 92.56 16.44 48.64 

Event III:

Ballast Failure Lamp & Ballast

EL2 87.8 41 W T12 & 0.65 BF Elec 103.62 5.38 54.29 

EL3 91.2 34 W T12 & 0.66 BF Mag 108.97 0.02 57.95 

Replacement EL3 91.2 34 W T12 & 0.75 BF Elec 94.85 14.14 54.03 

EL3 90.8 32.5 W T8 & 0.75 BF Elec 92.87 16.13 50.71 EL4 92.3 32.5 W T8 & 0.75 BF Elec 93.15 15.85 50.99 EL4 93.8 30.4 W T8 & 0.75 BF Elec 91.70 17.30 51.56 EL4 93.0 26.6 W T8 & 0.78 BF Elec 88.48 20.52 54.07 EL5 95.4 32.5 W T8 & 0.71 BF Elec 91.84 17.15 52.03 EL5 96.0 28.4 W T8 & 0.78 BF Elec 89.93 19.06 51.16 

Baseline Baseline/EL2 86.2 32.5 W T8 & 0.88 BF Elec 100.74 0.00 50.95 

EL3 91.2 34 W T12 & 0.75 BF Elec 97.16 3.58 56.34 

EL3 90.8 32.5 W T8 & 0.78 BF Elec 96.94 3.81 53.02 

Event V: New

Construction

and Renovation

New Lamp &

Ballast

Purchase

EL4 92.3 32.5 W T8 & 0.78 BF Elec 97.22 3.52 53.30 

EL4 93.8 30.4 W T8 & 0.78 BF Elec 95.46 5.29 53.87 

EL4 93.0 26.6 W T8 & 0.88 BF Elec 94.97 5.77 56.37 EL5 95.4 32.5 W T8 & 0.75 BF Elec 96.50 4.24 54.34 EL5 96.0 28.4 W T8 & 0.78 BF Elec 92.24 8.50 53.46 

8B­94

EE-2006-STD-0131 COMMENT 37.2
Table 8B.57 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin System Operating in 

Sector under the AEO2008 High Growth Electricity Price Trend Case and High Operating Hours

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 76.8 41 W T12 & 0.68 BF Mag 25.94 0.00 3.98 

A: Lamp

Replacement EL3 91.2 34 W T12 & 0.66 BF Mag 31.28 ­5.34 12.46 

EL1 80.5 41 W T12 & 0.65 BF Elec 33.11 ­7.17 51.00 

EL1 82.4 34 W T12 & 0.85 BF Elec 33.26 ­7.32 47.22 EL1 82.9 41 W T12 & 0.65 BF Elec 34.01 ­8.07 54.10 EL2 85.3 34 W T12 & 0.75 BF Elec 30.23 ­4.29 51.90 EL2 86.2 32.5 W T8 & 0.78 BF Elec 30.42 ­4.48 48.64 

Event I: Lamp

Failure B: Lamp &

Ballast

Replacement

EL2 87.8 41 W T12 & 0.65 BF Elec 34.07 ­8.13 54.29 

EL3 91.2 34 W T12 & 0.66 BF Mag 35.76 ­9.82 57.95 

EL3 91.2 34 W T12 & 0.75 BF Elec 30.85 ­4.92 54.03 

EL3 90.8 32.5 W T8 & 0.75 BF Elec 30.38 ­4.44 50.71 EL4 92.3 32.5 W T8 & 0.75 BF Elec 30.46 ­4.52 50.99 EL4 93.8 30.4 W T8 & 0.75 BF Elec 29.88 ­3.94 51.56 EL4 93.0 26.6 W T8 & 0.78 BF Elec 28.50 ­2.56 54.07 

EL5 95.4 32.5 W T8 & 0.71 BF Elec 29.90 ­3.96 52.03 

EL5 96.0 28.4 W T8 & 0.78 BF Elec 29.26 ­3.32 51.16 

8B­95

EE-2006-STD-0131 COMMENT 37.2
Table 8B.58 LCC and PBP Results for a Two­Lamp 4­Foot 40W T12 Medium Bipin System Operating in 

Sector under the AEO2008 Low Growth Electricity Price Trend Case and High Operating Hours

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 76.8 41 W T12 & 0.68 BF Mag 25.06 0.00 3.98 

A: Lamp

Replacement EL3 91.2 34 W T12 & 0.66 BF Mag 30.53 ­5.47 12.46 

EL1 80.5 41 W T12 & 0.65 BF Elec 32.37 ­7.32 51.00 

EL1 82.4 34 W T12 & 0.85 BF Elec 32.47 ­7.42 47.22 EL1 82.9 41 W T12 & 0.65 BF Elec 33.28 ­8.22 54.10 EL2 85.3 34 W T12 & 0.75 BF Elec 29.63 ­4.57 51.90 EL2 86.2 32.5 W T8 & 0.78 BF Elec 29.77 ­4.71 48.64 

Event I: Lamp

Failure B: Lamp &

Ballast

Replacement

EL2 87.8 41 W T12 & 0.65 BF Elec 33.34 ­8.28 54.29 

EL3 91.2 34 W T12 & 0.66 BF Mag 35.01 ­9.95 57.95 

EL3 91.2 34 W T12 & 0.75 BF Elec 30.25 ­5.19 54.03 

EL3 90.8 32.5 W T8 & 0.75 BF Elec 29.75 ­4.69 50.71 EL4 92.3 32.5 W T8 & 0.75 BF Elec 29.83 ­4.78 50.99 EL4 93.8 30.4 W T8 & 0.75 BF Elec 29.29 ­4.23 51.56 EL4 93.0 26.6 W T8 & 0.78 BF Elec 27.99 ­2.93 54.07 

EL5 95.4 32.5 W T8 & 0.71 BF Elec 29.31 ­4.25 52.03 

EL5 96.0 28.4 W T8 & 0.78 BF Elec 28.69 ­3.63 51.16 

8B­96

EE-2006-STD-0131 COMMENT 37.2
8B.7.3.2 Product Class: 4­foot T5 miniature bipin high output ≤ 4,500K

For the 4­foot T5 miniature bipin high output product class with CCT less than or equal

to 4,500K in the industrial sector, DOE analyzed one baseline lamp: a 54W T5. For this

baseline, the analysis period is 3.9 years. Other key inputs consist of using medium lamp and

ballast prices. The following tables present the LCC savings and PBP results for the product

class under the AEO2008 high growth and low growth electricity price trend cases.

8B­97

EE-2006-STD-0131 COMMENT 37.2
Table 8B.59 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin High Output System Oper

Industrial Sector under the AEO2008 High Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 128.62 0.00 10.44 

A: Lamp

Replacement EL1 98.0 51 W T5 & 1 BF Elec 131.95 ­3.33 19.85 

Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 160.16 0.00 69.03 

Event III:

Ballast Failure Lamp and Ballast

Replacement

EL1 98.0 51 W T5 & 1 BF Elec 163.49 ­3.33 78.44 

Event V: New Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 161.41 0.00 71.33 

Construction New Lamp & EL1 92.9 53.8 W T5 & 1 BF Elec 104.38 57.02 76.36 1

and Renovation Ballast

Purchase EL1 98.0 51 W T5 & 1 BF Elec 103.32 58.09 80.74 1

8B­98

EE-2006-STD-0131 COMMENT 37.2
Table 8B.60 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin High Output System Oper

Industrial Sector under the AEO2008 Low Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 121.57 0.00 10.44 

A: Lamp

Replacement EL1 98.0 51 W T5 & 1 BF Elec 125.07 ­3.50 19.85 

Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 153.11 0.00 69.03 

Event III:

Ballast Failure Lamp and Ballast

Replacement

EL1 98.0 51 W T5 & 1 BF Elec 156.61 ­3.50 78.44 

Event V: New Baseline Baseline 76.6 53.8 W T5 & 1 BF Elec 154.35 0.00 71.33 

Construction New Lamp & EL1 92.9 53.8 W T5 & 1 BF Elec 99.96 54.39 76.36 1

and Renovation Ballast

Purchase EL1 98.0 51 W T5 & 1 BF Elec 99.00 55.35 80.74 1

8B­99

EE-2006-STD-0131 COMMENT 37.2
8B.7.3.3 Product Class: 4­foot T5 miniature bipin standard output ≤ 4,500K

For the 4­foot T5 miniature bipin standard output product class with CCT less than or

equal to 4,500K in the commercial sector, DOE analyzed one baseline lamp: a 28W T5. For this

baseline, the analysis period is 5.5 years. Other key inputs consist of using medium lamp and

ballast prices. The following tables present the LCC savings and PBP results for the product

class under the AEO2008 high growth and low growth electricity price trend cases.

8B­100

EE-2006-STD-0131 COMMENT 37.2
Table 8B.61 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin Standard Output System O

Commercial Sector under the AEO2008 High Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

Design Option LCC LCC Savings Installed Price

Op

Sa

(

Y

lms/W $ $ $ 

Event I: Lamp

Failure

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 115.69 0.00 9.39 

A: Lamp

Replacement EL2 111.5 26 W T5 & 1.15 BF Elec 114.33 1.36 14.86 

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 149.63 0.00 66.89 

Event III: EL1 104.3 27.8 W T5 & 0.95 BF Elec 139.24 10.39 70.65 

Ballast Failure Lamp & Ballast

Replacement EL2 109.7 27.8 W T5 & 0.9 BF Elec 137.90 11.73 72.85 

EL2 111.5 26 W T5 & 0.9 BF Elec 128.67 20.96 72.36 

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 150.99 0.00 69.20 

Event V: New

Construction

and Renovation

New Lamp &

Ballast

Purchase

EL1 104.3 27.8 W T5 & 0.95 BF Elec 107.11 43.88 72.96 

EL2 109.7 27.8 W T5 & 0.9 BF Elec 102.79 48.20 75.16 EL2 111.5 26 W T5 & 0.9 BF Elec 104.56 46.43 74.67 

8B­101

EE-2006-STD-0131 COMMENT 37.2
Table 8B.62 LCC and PBP Results for a Two­Lamp 4­Foot T5 Miniature Bipin Standard Output System O

Commercial Sector under the AEO2008 Low Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 109.94 0.00 9.39 

A: Lamp

Replacement EL2 111.5 26 W T5 & 1.15 BF Elec 108.84 1.10 14.86 

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 143.88 0.00 66.89 

Event III: EL1 104.3 27.8 W T5 & 0.95 BF Elec 134.26 9.62 70.65 

Ballast Failure Lamp & Ballast

Replacement EL2 109.7 27.8 W T5 & 0.9 BF Elec 133.11 10.77 72.85 

EL2 111.5 26 W T5 & 0.9 BF Elec 124.25 19.63 72.36 

Baseline Baseline 86.0 27.8 W T5 & 1.15 BF Elec 145.25 0.00 69.20 

Event V: New

Construction

and Renovation

New Lamp &

Ballast

Purchase

EL1 104.3 27.8 W T5 & 0.95 BF Elec 103.32 41.92 72.96 

EL2 109.7 27.8 W T5 & 0.9 BF Elec 99.26 45.99 75.16 EL2 111.5 26 W T5 & 0.9 BF Elec 101.01 44.23 74.67 

8B­102

EE-2006-STD-0131 COMMENT 37.2
8B.7.3.4 Product Class: 8­foot single pin slimline ≤ 4,500K

The following tables present the findings of an LCC analysis on the three 8­foot single

pin slimline GSFL baselines operating in the commercial sector with a CCT less than or equal to

4,500K, considering AEO2008 high and low growth electricity price trend cases. Key inputs

consist of using medium lamp and ballast prices and an analysis period of 4.0 years. Note: Lamp

replacement results in Event I are not shown for a 60W T12 lamp because there are no energy

saving lamp replacement options.

8B­103

EE-2006-STD-0131 COMMENT 37.2
Table 8B.63 LCC and PBP Results for a Two­Lamp 8­Foot 75W T12 Single Pin Slimline System Operatin

Commercial Sector under the AEO2008 High Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 85.6 75 W T12 & 0.94 BF Mag 203.19 0.00 16.16 

A: Lamp

Replacement EL3 97.5 60.5 W T12 & 0.88 BF Mag 165.38 37.82 19.43 1

Event I: Lamp

Failure B: Lamp &

Baseline 85.6 75 W T12 & 0.94 BF Mag 203.19 0.00 16.16 

EL1 87.3 75 W T12 & 0.85 BF Elec 214.07 ­10.87 95.31 

Ballast EL2 92.0 75 W T12 & 0.85 BF Elec 210.07 ­6.88 97.21 

Replacement EL3 94.8 60.1 W T8 & 1.18 BF Elec 229.95 ­26.76 109.87 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 180.39 22.81 92.82 1

Baseline Baseline 85.6 75 W T12 & 0.94 BF Mag 194.41 0.00 16.16 

Event II: EL1 87.3 75 W T12 & 0.85 BF Elec 215.11 ­20.70 97.62 

Standards Lamp & Ballast EL2 92.0 75 W T12 & 0.85 BF Elec 211.12 ­16.70 99.52 

Induced Retrofit Replacement EL3 94.8 60.1 W T8 & 1.18 BF Elec 230.99 ­36.58 112.18 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 181.43 12.99 95.12 1

Baseline Baseline 85.6 75 W T12 & 0.88 BF Elec 209.58 0.00 88.94 

Event III: EL1 87.3 75 W T12 & 0.85 BF Elec 214.07 ­4.48 95.31 

Ballast Failure Lamp & Ballast

Replacement EL2 92.0 75 W T12 & 0.85 BF Elec 210.07 ­0.49 97.21 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 180.39 29.20 92.82 

Event IV:

Ballast Retrofit

Baseline Baseline/EL3 94.8 60.1 W T8 & 1.18 BF Elec 230.99 0.00 112.18 

Lamp & Ballast

Replacement EL5 101.5 60.1 W T8 & 0.88 BF Elec 181.43 49.56 95.12 1

8B­104

EE-2006-STD-0131 COMMENT 37.2
Table 8B.64 LCC and PBP Results for a Two­Lamp 8­Foot 75W T12 Single Pin Slimline System Operatin

Commercial Sector under the AEO2008 Low Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 85.6 75 W T12 & 0.94 BF Mag 193.68 0.00 16.16 

A: Lamp

Replacement EL3 97.5 60.5 W T12 & 0.88 BF Mag 157.79 35.89 19.43 1

Event I: Lamp

Failure B: Lamp &

Baseline 85.6 75 W T12 & 0.94 BF Mag 193.68 0.00 16.16 

EL1 87.3 75 W T12 & 0.85 BF Elec 206.12 ­12.44 95.31 

Ballast EL2 92.0 75 W T12 & 0.85 BF Elec 202.13 ­8.45 97.21 

Replacement EL3 94.8 60.1 W T8 & 1.18 BF Elec 220.92 ­27.24 109.87 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 173.59 20.09 92.82 1

Baseline Baseline 85.6 75 W T12 & 0.94 BF Mag 184.90 0.00 16.16 

Event II: EL1 87.3 75 W T12 & 0.85 BF Elec 207.16 ­22.26 97.62 

Standards Lamp & Ballast EL2 92.0 75 W T12 & 0.85 BF Elec 203.17 ­18.27 99.52 

Induced Retrofit Replacement EL3 94.8 60.1 W T8 & 1.18 BF Elec 221.96 ­37.06 112.18 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 174.63 10.27 95.12 1

Baseline Baseline 85.6 75 W T12 & 0.88 BF Elec 201.46 0.00 88.94 

Event III: EL1 87.3 75 W T12 & 0.85 BF Elec 206.12 ­4.66 95.31 

Ballast Failure Lamp & Ballast

Replacement EL2 92.0 75 W T12 & 0.85 BF Elec 202.13 ­0.67 97.21 

EL5 101.5 60.1 W T8 & 0.88 BF Elec 173.59 27.86 92.82 

Event IV:

Ballast Retrofit

Baseline Baseline/EL3 94.8 60.1 W T8 & 1.18 BF Elec 221.96 0.00 112.18 

Lamp & Ballast

Replacement EL5 101.5 60.1 W T8 & 0.88 BF Elec 174.63 47.33 95.12 1

8B­105

EE-2006-STD-0131 COMMENT 37.2
Table 8B.65 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin Slimline System Operatin

Commercial Sector under the AEO2008 High Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Mag 160.43 0.00 11.33 

EL2 92.6 60.5 W T12 & 0.85 BF Elec 177.24 ­16.81 88.79 

Event I: Lamp

Failure B: Lamp &

EL3 97.5 60.5 W T12 & 0.85 BF Elec 176.36 ­15.93 92.21 

Ballast EL3 94.8 60.1 W T8 & 0.88 BF Elec 176.89 ­16.46 86.72 

Replacement

EL4 98.2 60.1 W T8 & 0.78 BF Elec 167.06 ­6.63 91.10 

EL5 101.8 57 W T8 & 0.78 BF Elec 164.48 ­4.06 91.48 EL5 101.5 60.1 W T8 & 0.78 BF Elec 166.18 ­5.75 92.82 

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Mag 154.06 0.00 11.33 

EL2 92.6 60.5 W T12 & 0.85 BF Elec 178.28 ­24.22 91.10 

Event II:

Standards

Induced Retrofit Lamp & Ballast

Replacement

EL3 97.5 60.5 W T12 & 0.85 BF Elec 177.40 ­23.34 94.52 

EL3 94.8 60.1 W T8 & 0.88 BF Elec 177.93 ­23.87 89.03 EL4 98.2 60.1 W T8 & 0.78 BF Elec 168.10 ­14.04 93.41 

EL5 101.8 57 W T8 & 0.78 BF Elec 165.52 ­11.46 93.79 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 167.22 ­13.16 95.12 

8B­106

EE-2006-STD-0131 COMMENT 37.2
Table 8B.65 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin Slimline System Operatin

Commercial Sector under the AEO2008 High Growth Electricity Price Trend Case (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Elec 174.86 0.00 84.11 

EL2 92.6 60.5 W T12 & 0.85 BF Elec 177.24 ­2.38 88.79 

Event III:

Ballast Failure Lamp & Ballast EL3 97.5 60.5 W T12 & 0.85 BF Elec 176.36 ­1.50 92.21 

Replacement EL4 98.2 60.1 W T8 & 0.78 BF Elec 167.06 7.80 91.10 

EL5 101.8 57 W T8 & 0.78 BF Elec 164.48 10.37 91.48 EL5 101.5 60.1 W T8 & 0.78 BF Elec 166.18 8.68 92.82 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 177.93 0.00 89.03 

Event IV: EL4 98.2 60.1 W T8 & 0.78 BF Elec 168.10 9.83 93.41 

Ballast Retrofit Lamp & Ballast

Replacement EL5 101.8 57 W T8 & 0.78 BF Elec 165.52 12.41 93.79 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 167.22 10.71 95.12 

8B­107

EE-2006-STD-0131 COMMENT 37.2
Table 8B.66 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin Slimline System Operatin

Commercial Sector under the AEO2008 Low Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Mag 152.84 0.00 11.33 

EL2 92.6 60.5 W T12 & 0.85 BF Elec 170.79 ­17.96 88.79 

Event I: Lamp

Failure B: Lamp &

EL3 97.5 60.5 W T12 & 0.85 BF Elec 169.92 ­17.08 92.21 

Ballast EL3 94.8 60.1 W T8 & 0.88 BF Elec 170.10 ­17.26 86.72 

Replacement

EL4 98.2 60.1 W T8 & 0.78 BF Elec 161.01 ­8.17 91.10 

EL5 101.8 57 W T8 & 0.78 BF Elec 158.31 ­5.47 91.48 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 160.13 ­7.29 92.82 

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Mag 146.48 0.00 11.33 

EL2 92.6 60.5 W T12 & 0.85 BF Elec 171.84 ­25.36 91.10 

Event II:

Standards

Induced Retrofit Lamp & Ballast

Replacement

EL3 97.5 60.5 W T12 & 0.85 BF Elec 170.96 ­24.48 94.52 

EL3 94.8 60.1 W T8 & 0.88 BF Elec 171.14 ­24.66 89.03 EL4 98.2 60.1 W T8 & 0.78 BF Elec 162.05 ­15.58 93.41 

EL5 101.8 57 W T8 & 0.78 BF Elec 159.35 ­12.88 93.79 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 161.17 ­14.69 95.12 

8B­108

EE-2006-STD-0131 COMMENT 37.2
Table 8B.66 LCC and PBP Results for a Two­Lamp 8­Foot 60W T12 Single Pin Slimline System Operatin

Commercial Sector under the AEO2008 Low Growth Electricity Price Trend Case (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline/EL1 87.6 60.5 W T12 & 0.88 BF Elec 168.23 0.00 84.11 

EL2 92.6 60.5 W T12 & 0.85 BF Elec 170.79 ­2.56 88.79 

Event III:

Ballast Failure Lamp & Ballast EL3 97.5 60.5 W T12 & 0.85 BF Elec 169.92 ­1.68 92.21 

Replacement EL4 98.2 60.1 W T8 & 0.78 BF Elec 161.01 7.22 91.10 

EL5 101.8 57 W T8 & 0.78 BF Elec 158.31 9.92 91.48 EL5 101.5 60.1 W T8 & 0.78 BF Elec 160.13 8.10 92.82 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 171.14 0.00 89.03 

Event IV: EL4 98.2 60.1 W T8 & 0.78 BF Elec 162.05 9.08 93.41 

Ballast Retrofit Lamp & Ballast

Replacement EL5 101.8 57 W T8 & 0.78 BF Elec 159.35 11.78 93.79 

EL5 101.5 60.1 W T8 & 0.78 BF Elec 161.17 9.97 95.12 

8B­109

EE-2006-STD-0131 COMMENT 37.2
Table 8B.67 LCC and PBP Results for a Two­Lamp 8­Foot 59W T8 Single Pin Slimline System Operatin

Sector under the AEO2008 High Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 143.54 0.00 12.74 

A: Lamp EL5 101.8 57 W T8 & 0.88 BF Elec 136.88 6.66 17.50 

Replacement EL5 103.6 55 W T8 & 0.88 BF Elec 132.76 10.78 16.68 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 176.89 0.00 86.72 

Event III:

Ballast Failure Lamp & Ballast

EL4 98.2 60.1 W T8 & 0.85 BF Elec 177.01 ­0.12 91.10 

EL5 101.8 57 W T8 & 0.85 BF Elec 168.50 8.39 91.48 

Replacement EL5 101.5 60.1 W T8 & 0.78 BF Elec 166.18 10.71 92.82 

EL5 103.6 55 W T8 & 0.88 BF Elec 166.11 10.78 90.67 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 177.93 0.00 89.03 

Event V: New EL4 98.2 60.1 W T8 & 0.85 BF Elec 178.05 ­0.12 93.41 

Construction New Lamp & EL5 101.8 57 W T8 & 0.85 BF Elec 169.54 8.39 93.79 

and Renovation Ballast

Purchase EL5 101.5 60.1 W T8 & 0.78 BF Elec 167.22 10.71 95.12 

EL5 103.6 55 W T8 & 0.88 BF Elec 167.15 10.78 92.98 

8B­110

EE-2006-STD-0131 COMMENT 37.2
Table 8B.68 LCC and PBP Results for a Two­Lamp 8­Foot 59W T8 Single Pin Slimline System Operating 

Sector under the AEO2008 Low Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Event I: Lamp

Failure

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 136.74 0.00 12.74 

A: Lamp EL5 101.8 57 W T8 & 0.88 BF Elec 130.40 6.34 17.50 

Replacement EL5 103.6 55 W T8 & 0.88 BF Elec 126.61 10.13 16.68 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 170.10 0.00 86.72 

Event III:

Ballast Failure Lamp & Ballast

EL4 98.2 60.1 W T8 & 0.85 BF Elec 170.44 ­0.34 91.10 

EL5 101.8 57 W T8 & 0.85 BF Elec 162.12 7.97 91.48 

Replacement EL5 101.5 60.1 W T8 & 0.78 BF Elec 160.13 9.97 92.82 

EL5 103.6 55 W T8 & 0.88 BF Elec 159.96 10.13 90.67 

Baseline Baseline/EL3 94.8 60.1 W T8 & 0.88 BF Elec 171.14 0.00 89.03 

Event V: New EL4 98.2 60.1 W T8 & 0.85 BF Elec 171.48 ­0.34 93.41 

Construction New Lamp & EL5 101.8 57 W T8 & 0.85 BF Elec 163.16 7.97 93.79 

and Renovation Ballast

Purchase EL5 101.5 60.1 W T8 & 0.78 BF Elec 161.17 9.97 95.12 

EL5 103.6 55 W T8 & 0.88 BF Elec 161.00 10.13 92.98 

8B­111

EE-2006-STD-0131 COMMENT 37.2
8B.7.3.5 Product Class: 8­foot recessed double contact HO ≤ 4,500K

The following tables present the findings of an LCC analysis on the two 8­foot recessed

double contact high output GSFL baselines operating in the industrial sector, considering

AEO2008 high and low growth electricity price trend cases. Key inputs consist of using an

analysis period of 2.3 years. Note: Lamp replacement results in Event I are not shown for a 95W

T12 lamp because there are no energy saving lamp replacement options.

8B­112

EE-2006-STD-0131 COMMENT 37.2
Table 8B.69 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double Contact HO Syste

Industrial Sector under the AEO2008 High Growth Electricity Price Trend Case

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

S

(

Y

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 167.61 0.00 19.74 

A: Lamp EL3 87.6 97 W T12 & 0.91 BF Mag 159.24 8.38 32.38 

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 159.86 7.75 33.01 

Event I: Lamp EL1 83.2 113 W T12 & 0.88 BF Elec 186.68 ­19.07 113.23 

Failure EL3 87.6 97 W T12 & 0.91 BF Mag 184.97 ­17.35 110.24 

B: Lamp & Ballast

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 185.59 ­17.98 110.86 

EL3 88.9 97 W T12 & 0.9 BF Elec 176.22 ­8.60 114.96 EL5 95.3 86 W T8 & 0.88 BF Elec 149.52 18.09 124.19 

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 157.00 0.00 19.74 

EL1 83.2 113 W T12 & 0.88 BF Elec 187.44 ­30.44 115.54 

Event II: Standards EL3 87.6 97 W T12 & 0.91 BF Mag 185.73 ­28.73 112.54 

Induced Retrofit Lamp & Ballast

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 186.35 ­29.35 113.17 

EL3 88.9 97 W T12 & 0.9 BF Elec 176.98 ­19.98 117.27 EL5 95.3 86 W T8 & 0.88 BF Elec 150.28 6.72 126.49 

8B­113

EE-2006-STD-0131 COMMENT 37.2
Table 8B.69 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double Contact HO Syste

Industrial Sector under the AEO2008 High Growth Electricity Price Trend Case (continued)

Event Response Efficacy Level Rated Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installe

Price

$

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 193.34 0.00 97.60 

EL1 83.2 113 W T12 & 0.88 BF Elec 186.68 6.66 113.23 

Event III: Ballast EL3 87.6 97 W T12 & 0.91 BF Mag 184.97 8.38 110.24 

Failure Lamp & Ballast

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 185.59 7.75 110.86 

EL3 88.9 97 W T12 & 0.9 BF Elec 176.22 17.13 114.96 EL5 95.3 86 W T8 & 0.88 BF Elec 149.52 43.82 124.19 

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 194.10 0.00 99.90 

EL1 83.2 113 W T12 & 0.88 BF Elec 187.44 6.66 115.54 

EL2 86.1 97 W T12 & 0.9 BF Elec 187.66 6.45 104.32 EL2 86.1 97 W T12 & 0.91 BF Mag 196.20 ­2.10 100.22 

Event V: New EL3 87.6 97 W T12 & 0.9 BF Elec 198.19 ­4.09 116.64 

Construction and New Lamp & EL3 87.6 97 W T12 & 0.91 BF Mag 185.73 8.38 112.54 

Renovation Ballast Purchase EL3 88.9 97 W T12 & 0.9 BF Elec 176.98 17.13 117.27 

EL3 88.9 97 W T12 & 0.91 BF Mag 186.35 7.75 113.17 EL4 91.9 86 W T8 & 0.88 BF Elec 179.67 14.43 123.27 EL4 93.0 86 W T8 & 0.81 BF Elec 189.31 4.80 123.60 EL5 95.3 86 W T8 & 0.81 BF Elec 177.24 16.87 126.49 

8B­114

EE-2006-STD-0131 COMMENT 37.2
Table 8B.70 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double Contact HO Syste

Industrial Sector under the AEO2008 Low Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 158.82 0.00 19.74 

A: Lamp EL3 87.6 97 W T12 & 0.91 BF Mag 151.70 7.11 32.38 

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 152.33 6.49 33.01 

Event I: Lamp EL1 83.2 113 W T12 & 0.88 BF Elec 179.06 ­20.24 113.23 

Failure

B: Lamp & EL3 87.6 97 W T12 & 0.91 BF Mag 177.43 ­18.61 110.24 

Ballast EL3 88.9 97 W T12 & 0.91 BF Mag 178.06 ­19.24 110.86 

Replacement EL3 88.9 97 W T12 & 0.9 BF Elec 169.32 ­10.51 114.96 1

EL5 95.3 86 W T8 & 0.88 BF Elec 143.58 15.24 124.19 2

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 148.21 0.00 19.74 

EL1 83.2 113 W T12 & 0.88 BF Elec 179.82 ­31.62 115.54 

Event II:

Standards

Induced Retrofit

Lamp & Ballast

Replacement

EL3 87.6 97 W T12 & 0.91 BF Mag 178.19 ­29.99 112.54 

EL3 88.9 97 W T12 & 0.91 BF Mag 178.82 ­30.61 113.17 EL3 88.9 97 W T12 & 0.9 BF Elec 170.09 ­21.88 117.27 1EL5 95.3 86 W T8 & 0.88 BF Elec 144.34 3.86 126.49 2

8B­115

EE-2006-STD-0131 COMMENT 37.2
Table 8B.70 LCC and PBP Results for a Two­Lamp 8­Foot 110W T12 Recessed Double Contact HO Syste

Industrial Sector under the AEO2008 Low Growth Electricity Price Trend Case (continued)

Event Response Efficacy Level Rated Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installe

Price

$

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 184.54 0.00 97.60 

EL1 83.2 113 W T12 & 0.88 BF Elec 179.06 5.49 113.23 

Event III: Ballast EL3 87.6 97 W T12 & 0.91 BF Mag 177.43 7.11 110.24 

Failure Lamp & Ballast

Replacement EL3 88.9 97 W T12 & 0.91 BF Mag 178.06 6.49 110.86 

EL3 88.9 97 W T12 & 0.9 BF Elec 169.32 15.22 114.96 EL5 95.3 86 W T8 & 0.88 BF Elec 143.58 40.96 124.19 

Baseline Baseline 80.1 113 W T12 & 0.95 BF Mag 185.31 0.00 99.90 

EL1 83.2 113 W T12 & 0.88 BF Elec 179.82 5.49 115.54 

EL2 86.1 97 W T12 & 0.9 BF Elec 179.77 5.54 104.32 EL2 86.1 97 W T12 & 0.91 BF Mag 187.68 ­2.37 100.22 

Event V: New EL3 87.6 97 W T12 & 0.9 BF Elec 190.45 ­5.14 116.64 

Construction and New Lamp & EL3 87.6 97 W T12 & 0.91 BF Mag 178.19 7.11 112.54 

Renovation Ballast Purchase EL3 88.9 97 W T12 & 0.9 BF Elec 170.09 15.22 117.27 

EL3 88.9 97 W T12 & 0.91 BF Mag 178.82 6.49 113.17 EL4 91.9 86 W T8 & 0.88 BF Elec 172.32 12.99 123.27 EL4 93.0 86 W T8 & 0.81 BF Elec 181.87 3.44 123.60 EL5 95.3 86 W T8 & 0.81 BF Elec 170.37 14.93 126.49 

8B­116

EE-2006-STD-0131 COMMENT 37.2
Table 8B.71 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double Contact HO System 

Industrial Sector under the AEO2008 High Growth Electricity Price Trend Case

Event Response Efficacy Level Rated Lamp Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

S

(

Y

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 140.78 0.00 13.92 

EL2 86.1 97 W T12 & 0.89 BF Elec 160.59 ­19.81 102.01 

Event I: Lamp

Failure B: Lamp & Ballast

EL3 87.6 97 W T12 & 0.88 BF Elec 170.23 ­29.46 114.33 

EL3 88.9 97 W T12 & 0.88 BF Elec 170.86 ­30.08 114.96 

Replacement EL4 91.9 86 W T8 & 0.88 BF Elec 144.32 ­3.54 120.96 

EL4 93.0 86 W T8 & 0.88 BF Elec 147.48 ­6.71 121.29 

EL5 95.3 86 W T8 & 0.81 BF Elec 143.96 ­3.18 124.19 

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 133.09 0.00 13.92 

EL2 86.1 97 W T12 & 0.89 BF Elec 161.35 ­28.26 104.32 

Event II: Standards

Induced Retrofit Lamp & Ballast

Replacement

EL3 87.6 97 W T12 & 0.88 BF Elec 171.00 ­37.91 116.64 

EL3 88.9 97 W T12 & 0.88 BF Elec 171.62 ­38.53 117.27 EL4 91.9 86 W T8 & 0.88 BF Elec 145.08 ­11.99 123.27 

EL4 93.0 86 W T8 & 0.88 BF Elec 148.25 ­15.16 123.60 

EL5 95.3 86 W T8 & 0.81 BF Elec 144.72 ­11.63 126.49 

8B­117

EE-2006-STD-0131 COMMENT 37.2
Table 8B.71 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double Contact HO System 

Industrial Sector under the AEO2008 High Growth Electricity Price Trend Case (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 166.50 0.00 91.77 

EL2 86.1 97 W T12 & 0.89 BF Elec 160.59 5.92 102.01 

Event III:

Ballast Failure Lamp & Ballast

EL3 87.6 97 W T12 & 0.88 BF Elec 170.23 ­3.73 114.33 

EL3 88.9 97 W T12 & 0.88 BF Elec 170.86 ­4.36 114.96 

Replacement EL4 91.9 86 W T8 & 0.88 BF Elec 144.32 22.19 120.96 1

EL4 93.0 86 W T8 & 0.88 BF Elec 147.48 19.02 121.29 1EL5 95.3 86 W T8 & 0.81 BF Elec 143.96 22.55 124.19 1

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 167.27 0.00 94.08 

EL2 86.1 97 W T12 & 0.89 BF Elec 161.35 5.92 104.32 

Event V: New EL3 87.6 97 W T12 & 0.88 BF Elec 171.00 ­3.73 116.64 

Construction New Lamp & EL3 88.9 97 W T12 & 0.88 BF Elec 171.62 ­4.36 117.27 

and Renovation Ballast

Purchase EL4 91.9 86 W T8 & 0.88 BF Elec 145.08 22.19 123.27 1

EL4 93.0 86 W T8 & 0.88 BF Elec 148.25 19.02 123.60 1EL5 95.3 86 W T8 & 0.81 BF Elec 144.72 22.55 126.49 1

8B­118

EE-2006-STD-0131 COMMENT 37.2
Table 8B.72 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double Contact HO System 

Industrial Sector under the AEO2008 Low Growth Electricity Price Trend Case

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 133.24 0.00 13.92 

EL2 86.1 97 W T12 & 0.89 BF Elec 153.86 ­20.62 102.01 

Event I: Lamp

Failure

B: Lamp &

EL3 87.6 97 W T12 & 0.88 BF Elec 163.66 ­30.42 114.33 

EL3 88.9 97 W T12 & 0.88 BF Elec 164.29 ­31.05 114.96 

Replacement

Ballast

EL4 91.9 86 W T8 & 0.88 BF Elec 138.38 ­5.14 120.96 1

EL4 93.0 86 W T8 & 0.88 BF Elec 141.54 ­8.30 121.29 1EL5 95.3 86 W T8 & 0.81 BF Elec 138.35 ­5.11 124.19 1

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 125.56 0.00 13.92 

EL2 86.1 97 W T12 & 0.89 BF Elec 154.62 ­29.06 104.32 

Event II: EL3 87.6 97 W T12 & 0.88 BF Elec 164.43 ­38.87 116.64 

Standards Lamp & Ballast EL3 88.9 97 W T12 & 0.88 BF Elec 165.05 ­39.50 117.27 

Induced Retrofit Replacement EL4 91.9 86 W T8 & 0.88 BF Elec 139.14 ­13.59 123.27 1

EL4 93.0 86 W T8 & 0.88 BF Elec 142.31 ­16.75 123.60 1EL5 95.3 86 W T8 & 0.81 BF Elec 139.11 ­13.56 126.49 1

8B­119

EE-2006-STD-0131 COMMENT 37.2
Table 8B.72 LCC and PBP Results for a Two­Lamp 8­Foot 95W T12 Recessed Double Contact HO System 

Industrial Sector under the AEO2008 Low Growth Electricity Price Trend Case (continued)

Event Response Efficacy Level

Rated

Lamp

Efficacy

lms/W

Design Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 158.97 0.00 91.77 

EL2 86.1 97 W T12 & 0.89 BF Elec 153.86 5.11 102.01 

Event III:

Ballast Failure Lamp & Ballast

EL3 87.6 97 W T12 & 0.88 BF Elec 163.66 ­4.70 114.33 

EL3 88.9 97 W T12 & 0.88 BF Elec 164.29 ­5.32 114.96 

Replacement EL4 91.9 86 W T8 & 0.88 BF Elec 138.38 20.59 120.96 1

EL4 93.0 86 W T8 & 0.88 BF Elec 141.54 17.42 121.29 1EL5 95.3 86 W T8 & 0.81 BF Elec 138.35 20.62 124.19 1

Baseline Baseline 82.5 97 W T12 & 0.91 BF Mag 159.73 0.00 94.08 

EL2 86.1 97 W T12 & 0.89 BF Elec 154.62 5.11 104.32 

Event V: New EL3 87.6 97 W T12 & 0.88 BF Elec 164.43 ­4.70 116.64 

Construction New Lamp & EL3 88.9 97 W T12 & 0.88 BF Elec 165.05 ­5.32 117.27 

and Renovation Ballast

Purchase EL4 91.9 86 W T8 & 0.88 BF Elec 139.14 20.59 123.27 1

EL4 93.0 86 W T8 & 0.88 BF Elec 142.31 17.42 123.60 1EL5 95.3 86 W T8 & 0.81 BF Elec 139.11 20.62 126.49 1

8B­120

EE-2006-STD-0131 COMMENT 37.2
8B.8 INCANDESCENT REFLECTOR RESULTS

DOE analyzed three IRL baselines in the commercial and residential sectors: a 90W

PAR38 lamp, a 75W PAR38 lamp, and a 50W PAR30 lamp. For each of the three baselines,

DOE conducts both probability analyses (based on Monte Carlo runs) and scenario analyses.

8B.8.1 Monte Carlo Results

Similar to GSFL, to characterize the LCC savings and Monte Carlo results for IRL DOE

developed tables to describe the results distributions. These tables document the average LCC

savings and percentages of building analyzed with positive and negative LCC savings for each

lamp design. In addition, to characterize the distribution of payback periods, DOE reports the

median and average payback period for every lamp design and EL. The following tables present

the LCC savings and PBP Monte Carlo results for the three IRL baselines operating in the

commercial and residential sectors. Key inputs consist of using the AEO2008 reference case

electricity prices and medium­range lamp prices.

8B­121

EE-2006-STD-0131 COMMENT 37.2
Table 8B.73 LCC and PBP Monte Carlo Results for a 90W PAR38 Lamp Operating in the Commercial S

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 14.6 90W, 14.6lm/W & 2500hrs, Halogen N/A N/A N/A 

85.7W, 15.3lm/W &

EL1 15.3 2500hrs, Improved Halogen ­0.02 35.1 64.9 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 15.9 82.5W, 15.9lm/W & 6000hrs, Long Life HIR 5.61 100.0 0.0 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 16.6 79W, 16.6lm/W & 3000hrs, Improved Halogen (Silver) 3.17 100.0 0.0 

EL3 18.0 70W, 18lm/W & 3000hrs, HIR 5.42 100.0 0.0 

EL4 19.8 66W, 19.8lm/W & 4000hrs, Improved HIR 7.35 100.0 0.0 

EL5 21.0 60W, 21lm/W & 4200hrs, Improved HIR Plus 8.66 100.0 0.0 

8B­122

EE-2006-STD-0131 COMMENT 37.2
Table 8B.74 LCC and PBP Monte Carlo Results for a 90W PAR38 Lamp Operating in the Residential Se

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline 14.6 90W, 14.6lm/W & 2500hrs, Halogen N/A N/A N/A 

85.7W, 15.3lm/W &

EL1 15.3 2500hrs, Improved Halogen 0.17 56.1 43.9 

(Xenon)

Event I: Lamp

Failure; or Event Lamp EL2 15.9 82.5W, 15.9lm/W & 6000hrs, Long Life HIR 4.62 100.0 0.0 

V: New

Construction and

Renovation

Replacement or

New Lamp

Purchase

EL2 16.6 79W, 16.6lm/W & 3000hrs, Improved Halogen (Silver) 3.02 100.0 0.0 

EL3 18.0 70W, 18lm/W & 3000hrs, HIR 5.57 100.0 0.0 

EL4 19.8 66W, 19.8lm/W & 4000hrs, Improved HIR 7.17 100.0 0.0 

EL5 21.0 60W, 21lm/W & 4200hrs, Improved HIR Plus 8.80 100.0 0.0 

8B­123

EE-2006-STD-0131 COMMENT 37.2
Table 8B.75 LCC and PBP Monte Carlo Results for a 75W PAR38 Lamp Operating in the Commercial S

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 14.0 75W, 14lm/W & 2500hrs, Halogen N/A N/A N/A 

71.7W, 14.6lm/W &

EL1 14.6 2500hrs, Improved Halogen ­0.28 16.4 83.6 

(Xenon)

Event I: Lamp EL2 15.3 68.8W, 15.3lm/W & 6000hrs, Long Life HIR 5.29 100.0 0.0 

Failure; or Event

V: New

Construction and

Lamp

Replacement or

EL2 15.9 66W, 15.9lm/W & 3000hrs, Improved Halogen (Silver) 2.67 100.0 0.0 

Renovation New Lamp

Purchase EL3 17.5 60W, 17.5lm/W & 3000hrs, HIR 4.12 100.0 0.0 

EL4 19.1 55W, 19.1lm/W & 4000hrs, Improved HIR 6.33 100.0 0.0 EL5 20.3 51.7W, 20.3lm/W & 4200hrs, Improved HIR Plus 6.92 100.0 0.0 

8B­124

EE-2006-STD-0131 COMMENT 37.2
Table 8B.76 LCC and PBP Monte Carlo Results for a 75W PAR38 Lamp Operating in the Residential Se

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 14.0 75W, 14lm/W & 2500hrs, Halogen N/A N/A N/A 

71.7W, 14.6lm/W &

EL1 14.6 2500hrs, Improved Halogen ­0.13 28.8 71.2 

(Xenon)

Event I: Lamp EL2 15.3 68.8W, 15.3lm/W & 6000hrs, Long Life HIR 4.23 100.0 0.0 

Failure; or Event

V: New

Construction and

Lamp

Replacement or

EL2 15.9 66W, 15.9lm/W & 3000hrs, Improved Halogen (Silver) 2.41 100.0 0.0 

Renovation New Lamp

Purchase EL3 17.5 60W, 17.5lm/W & 3000hrs, HIR 4.06 100.0 0.0 

EL4 19.1 55W, 19.1lm/W & 4000hrs, Improved HIR 5.96 100.0 0.0 EL5 20.3 51.7W, 20.3lm/W & 4200hrs, Improved HIR Plus 6.78 100.0 0.0 

8B­125

EE-2006-STD-0131 COMMENT 37.2
Table 8B.77 LCC and PBP Monte Carlo Results for a 50W PAR30 Lamp Operating in the Commercial S

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 12.6 50W, 12.6lm/W & 3000hrs, Halogen N/A N/A N/A 

47.8W, 13.2lm/W &

EL1 13.2 3000hrs, Improved Halogen ­0.34 6.0 94.0 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 13.5 46W, 13.5lm/W & 6000hrs, Long Life HIR 2.80 100.0 0.0 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 14.0 45W, 14lm/W & 3000hrs, Improved Halogen (Silver) ­0.03 34.5 65.5 

EL3 15.1 41.8W, 15.1lm/W & 3000hrs, HIR 0.66 96.9 3.1 EL4 17.0 40W, 17lm/W & 4000hrs, Improved HIR 1.85 100.0 0.0 EL5 19.1 40W, 19.1lm/W & 4200hrs, Improved HIR Plus 1.54 100.0 0.0 

8B­126

EE-2006-STD-0131 COMMENT 37.2
Table 8B.78 LCC and PBP Monte Carlo Results for a 50W PAR30 Lamp Operating in the Residential Se

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option

Average

LCC

Savings

$

Net Benefit

%

Net Cost

%

M

Baseline Baseline 12.6 50W, 12.6lm/W & 3000hrs, Halogen N/A N/A N/A 

47.8W, 13.2lm/W &

EL1 13.2 3000hrs, Improved Halogen ­0.28 9.1 90.9 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 13.5 46W, 13.5lm/W & 6000hrs, Long Life HIR 2.23 100.0 0.0 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 14.0 45W, 14lm/W & 3000hrs, Improved Halogen (Silver) 0.11 43.2 56.8 

EL3 15.1 41.8W, 15.1lm/W & 3000hrs, HIR 0.89 98.6 1.4 EL4 17.0 40W, 17lm/W & 4000hrs, Improved HIR 1.69 99.7 0.3 EL5 19.1 40W, 19.1lm/W & 4200hrs, Improved HIR Plus 1.49 97.3 2.7 

8B.8.2 Lamp Price Scenario Results

As mentioned earlier, DOE also analyzed LCC savings and PBP results using a scenario analysis. Specif

LCC and PBP results are highly dependent on equipment prices, DOE examined several sensitivities to the medi

presented in Chapter 8. Chapter 7 described three prices (low, medium, and high) DOE developed for each IRL 

following tables present the findings of the LCC and PBP analyses on the three IRL baselines operating in the co

residential sectors, considering low lamp prices and high lamp prices. Key inputs consist of using AEO2008 refe

prices, average operating hours in each sector, and an analysis period of 0.9 years in the commercial sector and 3

residential sector.

8B­127

EE-2006-STD-0131 COMMENT 37.2
Table 8B.79 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Commercial Sector with Hi

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.6 90W, 14.6lm/W & 2500hrs, Halogen 36.18 0.00 7.91 

85.7W, 15.3lm/W &

EL1 15.3 2500hrs, Improved Halogen 36.63 ­0.44 9.16 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 15.9 82.5W, 15.9lm/W & 6000hrs, Long Life HIR 29.11 7.07 9.99 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 16.6 79W, 16.6lm/W & 3000hrs, Improved Halogen (Silver) 32.27 3.91 9.76 

EL3 18.0 70W, 18lm/W & 3000hrs, HIR 29.94 6.24 9.99 

EL4 19.8 66W, 19.8lm/W & 4000hrs, Improved HIR 27.82 8.37 11.75 

EL5 21.0 60W, 21lm/W & 4200hrs, Improved HIR Plus 26.68 9.50 12.50 

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Oper

C

Sav

(S

Ye

Event I: Lamp

Failure; or Event

V: New

Construction and

Renovation

Baseline Baseline 14.6 90W, 14.6lm/W & 2500hrs, Halogen 35.60 0.00 7.91 0

Lamp

Replacement or

New Lamp

Purchase

EL1 15.3

85.7W, 15.3lm/W &

2500hrs, Improved Halogen

(Xenon)

36.07 ­0.47 9.16 1

EL2 15.9 82.5W, 15.9lm/W & 6000hrs, Long Life HIR 28.58 7.03 9.99 2

8B­128

EE-2006-STD-0131 COMMENT 37.2
EL2 16.6 79W, 16.6lm/W & 3000hrs, Improved Halogen (Silver) 31.76 3.84 9.76 3

EL3 18.0 70W, 18lm/W & 3000hrs, HIR 29.49 6.11 9.99 5

EL4 19.8 66W, 19.8lm/W & 4000hrs, Improved HIR 27.39 8.21 11.75 7

EL5 21.0 60W, 21lm/W & 4200hrs, Improved HIR Plus 26.30 9.31 12.50 8

8B­129

EE-2006-STD-0131 COMMENT 37.2
Table 8B.80 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Residential Sector with Hig

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.6 90W, 14.6lm/W & 2500hrs, Halogen 35.14 0.00 6.84 

85.7W, 15.3lm/W &

EL1 15.3 2500hrs, Improved Halogen 35.40 ­0.26 8.10 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 15.9 82.5W, 15.9lm/W & 6000hrs, Long Life HIR 29.64 5.50 8.93 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 16.6 79W, 16.6lm/W & 3000hrs, Improved Halogen (Silver) 32.16 2.99 8.70 

EL3 18.0 70W, 18lm/W & 3000hrs, HIR 29.72 5.42 8.93 

EL4 19.8 66W, 19.8lm/W & 4000hrs, Improved HIR 28.07 7.07 10.69 

EL5 21.0 60W, 21lm/W & 4200hrs, Improved HIR Plus 26.43 8.72 11.44 

8B­130

EE-2006-STD-0131 COMMENT 37.2
Table 8B.81 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Commercial Sector with Lo

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.6 90W, 14.6lm/W & 2500hrs, Halogen 31.62 0.00 4.48 

85.7W, 15.3lm/W &

EL1 15.3 2500hrs, Improved Halogen 31.24 0.38 5.12 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 15.9 82.5W, 15.9lm/W & 6000hrs, Long Life HIR 26.61 5.02 5.53 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 16.6 79W, 16.6lm/W & 3000hrs, Improved Halogen (Silver) 27.93 3.70 5.41 

EL3 18.0 70W, 18lm/W & 3000hrs, HIR 25.48 6.15 5.53 

EL4 19.8 66W, 19.8lm/W & 4000hrs, Improved HIR 23.72 7.90 6.41 

EL5 21.0 60W, 21lm/W & 4200hrs, Improved HIR Plus 22.30 9.33 6.78 

8B­131

EE-2006-STD-0131 COMMENT 37.2
Table 8B.82 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Residential Sector with Low 

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.6 90W, 14.6lm/W & 2500hrs, Halogen 30.94 0.00 3.42 

85.7W, 15.3lm/W &

EL1 15.3 2500hrs, Improved Halogen 30.43 0.50 4.05 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 15.9 82.5W, 15.9lm/W & 6000hrs, Long Life HIR 27.07 3.87 4.47 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 16.6 79W, 16.6lm/W & 3000hrs, Improved Halogen (Silver) 27.81 3.13 4.35 

EL3 18.0 70W, 18lm/W & 3000hrs, HIR 25.25 5.68 4.47 

EL4 19.8 66W, 19.8lm/W & 4000hrs, Improved HIR 23.84 7.10 5.34 

EL5 21.0 60W, 21lm/W & 4200hrs, Improved HIR Plus 22.12 8.81 5.72 

8B­132

EE-2006-STD-0131 COMMENT 37.2
Table 8B.83 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Commercial Sector using H

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.0 75W, 14lm/W & 2500hrs, Halogen 31.91 0.00 7.91 

71.7W, 14.6lm/W &

EL1 14.6 2500hrs, Improved Halogen 32.64 ­0.73 9.16 

(Xenon)

Event I: Lamp EL2 15.3 68.8W, 15.3lm/W & 6000hrs, Long Life HIR 25.21 6.70 9.99 

Failure; or Event

V: New

Construction and

Lamp

Replacement or

EL2 15.9 66W, 15.9lm/W & 3000hrs, Improved Halogen (Silver) 28.57 3.34 9.76 

Renovation New Lamp

Purchase EL3 17.5 60W, 17.5lm/W & 3000hrs, HIR 27.09 4.82 9.99 

EL4 19.1 55W, 19.1lm/W & 4000hrs, Improved HIR 24.68 7.23 11.75 EL5 20.3 51.7W, 20.3lm/W & 4200hrs, Improved HIR Plus 24.32 7.59 12.50 

8B­133

EE-2006-STD-0131 COMMENT 37.2
Table 8B.84 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Residential Sector using Hig

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.0 75W, 14lm/W & 2500hrs, Halogen 30.69 0.00 6.84 

71.7W, 14.6lm/W &

EL1 14.6 2500hrs, Improved Halogen 31.25 ­0.56 8.10 

(Xenon)

Event I: Lamp EL2 15.3 68.8W, 15.3lm/W & 6000hrs, Long Life HIR 25.57 5.12 8.93 

Failure; or Event

V: New

Construction and

Lamp

Replacement or

EL2 15.9 66W, 15.9lm/W & 3000hrs, Improved Halogen (Silver) 28.30 2.39 8.70 

Renovation New Lamp

Purchase EL3 17.5 60W, 17.5lm/W & 3000hrs, HIR 26.75 3.94 8.93 

EL4 19.1 55W, 19.1lm/W & 4000hrs, Improved HIR 24.80 5.88 10.69 EL5 20.3 51.7W, 20.3lm/W & 4200hrs, Improved HIR Plus 23.96 6.73 11.44 

8B­134

EE-2006-STD-0131 COMMENT 37.2
Table 8B.85 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Commercial Sector using L

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.0 75W, 14lm/W & 2500hrs, Halogen 27.35 0.00 4.48 

71.7W, 14.6lm/W &

EL1 14.6 2500hrs, Improved Halogen 27.25 0.10 5.12 

(Xenon)

Event I: Lamp EL2 15.3 68.8W, 15.3lm/W & 6000hrs, Long Life HIR 22.70 4.65 5.53 

Failure; or Event

V: New

Construction and

Lamp

Replacement or

EL2 15.9 66W, 15.9lm/W & 3000hrs, Improved Halogen (Silver) 24.22 3.13 5.41 

Renovation New Lamp

Purchase EL3 17.5 60W, 17.5lm/W & 3000hrs, HIR 22.63 4.72 5.53 

EL4 19.1 55W, 19.1lm/W & 4000hrs, Improved HIR 20.58 6.76 6.41 EL5 20.3 51.7W, 20.3lm/W & 4200hrs, Improved HIR Plus 19.93 7.42 6.78 

8B­135

EE-2006-STD-0131 COMMENT 37.2
Table 8B.86 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Residential Sector using Low 

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.0 75W, 14lm/W & 2500hrs, Halogen 26.48 0.00 3.42 

71.7W, 14.6lm/W &

EL1 14.6 2500hrs, Improved Halogen 26.28 0.20 4.05 

(Xenon)

Event I: Lamp EL2 15.3 68.8W, 15.3lm/W & 6000hrs, Long Life HIR 23.00 3.48 4.47 

Failure; or Event

V: New

Construction and

Lamp

Replacement or

EL2 15.9 66W, 15.9lm/W & 3000hrs, Improved Halogen (Silver) 23.95 2.53 4.35 

Renovation New Lamp

Purchase EL3 17.5 60W, 17.5lm/W & 3000hrs, HIR 22.28 4.20 4.47 

EL4 19.1 55W, 19.1lm/W & 4000hrs, Improved HIR 20.57 5.91 5.34 EL5 20.3 51.7W, 20.3lm/W & 4200hrs, Improved HIR Plus 19.66 6.82 5.72 

8B­136

EE-2006-STD-0131 COMMENT 37.2
Table 8B.87 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Commercial Sector using H

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 12.6 50W, 12.6lm/W & 3000hrs, Halogen 21.35 0.00 7.10 

47.8W, 13.2lm/W &

EL1 13.2 3000hrs, Improved Halogen 21.98 ­0.63 8.36 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 13.5 46W, 13.5lm/W & 6000hrs, Long Life HIR 18.26 3.09 9.19 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 14.0 45W, 14lm/W & 3000hrs, Improved Halogen (Silver) 21.77 ­0.43 8.95 

EL3 15.1 41.8W, 15.1lm/W & 3000hrs, HIR 21.10 0.25 9.19 EL4 17.0 40W, 17lm/W & 4000hrs, Improved HIR 19.79 1.56 10.94 EL5 19.1 40W, 19.1lm/W & 4200hrs, Improved HIR Plus 20.37 0.98 11.70 

8B­137

EE-2006-STD-0131 COMMENT 37.2
Table 8B.88 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Residential Sector using Hig

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 12.6 50W, 12.6lm/W & 3000hrs, Halogen 20.88 0.00 6.04 

47.8W, 13.2lm/W &

EL1 13.2 3000hrs, Improved Halogen 21.49 ­0.60 7.29 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 13.5 46W, 13.5lm/W & 6000hrs, Long Life HIR 18.33 2.55 8.12 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 14.0 45W, 14lm/W & 3000hrs, Improved Halogen (Silver) 21.25 ­0.37 7.89 

EL3 15.1 41.8W, 15.1lm/W & 3000hrs, HIR 20.54 0.35 8.12 EL4 17.0 40W, 17lm/W & 4000hrs, Improved HIR 19.71 1.18 9.88 EL5 19.1 40W, 19.1lm/W & 4200hrs, Improved HIR Plus 19.88 1.00 10.64 

8B­138

EE-2006-STD-0131 COMMENT 37.2
Table 8B.89 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Commercial Sector using L

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 12.6 50W, 12.6lm/W & 3000hrs, Halogen 18.33 0.00 4.08 

47.8W, 13.2lm/W &

EL1 13.2 3000hrs, Improved Halogen 18.33 0.00 4.71 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 13.5 46W, 13.5lm/W & 6000hrs, Long Life HIR 15.98 2.35 5.12 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 14.0 45W, 14lm/W & 3000hrs, Improved Halogen (Silver) 17.83 0.50 5.01 

EL3 15.1 41.8W, 15.1lm/W & 3000hrs, HIR 17.04 1.29 5.12 EL4 17.0 40W, 17lm/W & 4000hrs, Improved HIR 16.00 2.33 6.00 EL5 19.1 40W, 19.1lm/W & 4200hrs, Improved HIR Plus 16.44 1.89 6.58 

8B­139

EE-2006-STD-0131 COMMENT 37.2
Table 8B.90 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Residential Sector using Low 

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 12.6 50W, 12.6lm/W & 3000hrs, Halogen 17.87 0.00 3.02 

47.8W, 13.2lm/W &

EL1 13.2 3000hrs, Improved Halogen 17.84 0.02 3.65 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 13.5 46W, 13.5lm/W & 6000hrs, Long Life HIR 16.00 1.87 4.06 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 14.0 45W, 14lm/W & 3000hrs, Improved Halogen (Silver) 17.31 0.56 3.94 

EL3 15.1 41.8W, 15.1lm/W & 3000hrs, HIR 16.48 1.39 4.06 EL4 17.0 40W, 17lm/W & 4000hrs, Improved HIR 15.79 2.07 4.94 EL5 19.1 40W, 19.1lm/W & 4200hrs, Improved HIR Plus 16.03 1.84 5.52 

8B.8.3 Operating Hour Scenario Results

In addition to analyzing lamp price sensitivities to the analysis, DOE also analyzes LCC and PBP sensitiv

hours. As discussed earlier, Monte Carlo results take into account distributions in operating hours across buildin

because the LCC and PBP results are highly dependent on equipment prices, DOE examined several sensitivities

residential sector, because there is a large range of hours across room types (not depicted in the operating hour di

building types) DOE analyzes high and low operating hour sensitivity LCC and PBP results. For residential inca

lamps, results using high operating hours (1,210 hours/ year: the average operating hours of a lamp placed in the 

family detached home) and low operating hours (183 hours/ year: the average operating hours of a lamp placed in 

family 2­4 unit home) are presented. These operating hours were obtained from the U.S. Lighting Market Chara

8B­140

EE-2006-STD-0131 COMMENT 37.2
Iii. The following tables depict these results for the residential sector using key inputs such as AEO2008 referenc

prices and average lamp prices. The high operating hour scenario uses an analysis period of 2.5 years and the low 

scenario uses an analysis period of 16.4 years.

Table 8B.91 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Residential Sector using Hig

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.6 90W, 14.6lm/W & 2500hrs, Halogen 33.79 0.00 5.13 

85.7W, 15.3lm/W &

EL1 15.3 2500hrs, Improved Halogen 33.61 0.18 6.07 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 15.9 82.5W, 15.9lm/W & 6000hrs, Long Life HIR 29.14 4.65 6.70 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 16.6 79W, 16.6lm/W & 3000hrs, Improved Halogen (Silver) 30.73 3.06 6.52 

EL3 18.0 70W, 18lm/W & 3000hrs, HIR 28.15 5.64 6.70 

EL4 19.8 66W, 19.8lm/W & 4000hrs, Improved HIR 26.59 7.20 8.02 

EL5 21.0 60W, 21lm/W & 4200hrs, Improved HIR Plus 24.89 8.90 8.59 

8B­141

EE-2006-STD-0131 COMMENT 37.2
Table 8B.92 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Residential Sector using Low 

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.6 90W, 14.6lm/W & 2500hrs, Halogen 25.26 0.00 5.13 

85.7W, 15.3lm/W &

EL1 15.3 2500hrs, Improved Halogen 25.43 ­0.17 6.07 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 15.9 82.5W, 15.9lm/W & 6000hrs, Long Life HIR 23.01 2.25 6.70 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 16.6 79W, 16.6lm/W & 3000hrs, Improved Halogen (Silver) 23.48 1.78 6.52 

EL3 18.0 70W, 18lm/W & 3000hrs, HIR 21.73 3.53 6.70 

EL4 19.8 66W, 19.8lm/W & 4000hrs, Improved HIR 21.35 3.92 8.02 

EL5 21.0 60W, 21lm/W & 4200hrs, Improved HIR Plus 20.44 4.82 8.59 

8B­142

EE-2006-STD-0131 COMMENT 37.2
Table 8B.93 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Residential Sector using Hig

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.0 75W, 14lm/W & 2500hrs, Halogen 29.19 0.00 5.13 

71.7W, 14.6lm/W &

EL1 14.6 2500hrs, Improved Halogen 29.32 ­0.13 6.07 

(Xenon)

Event I: Lamp EL2 15.3 68.8W, 15.3lm/W & 6000hrs, Long Life HIR 24.94 4.25 6.70 

Failure; or Event

V: New

Construction and

Lamp

Replacement or

EL2 15.9 66W, 15.9lm/W & 3000hrs, Improved Halogen (Silver) 26.75 2.44 6.52 

Renovation New Lamp

Purchase EL3 17.5 60W, 17.5lm/W & 3000hrs, HIR 25.09 4.11 6.70 

EL4 19.1 55W, 19.1lm/W & 4000hrs, Improved HIR 23.22 5.97 8.02 EL5 20.3 51.7W, 20.3lm/W & 4200hrs, Improved HIR Plus 22.35 6.84 8.59 

8B­143

EE-2006-STD-0131 COMMENT 37.2
Table 8B.94 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Residential Sector using Low 

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.0 75W, 14lm/W & 2500hrs, Halogen 22.04 0.00 5.13 

71.7W, 14.6lm/W &

EL1 14.6 2500hrs, Improved Halogen 22.42 ­0.38 6.07 

(Xenon)

Event I: Lamp EL2 15.3 68.8W, 15.3lm/W & 6000hrs, Long Life HIR 20.07 1.97 6.70 

Failure; or Event

V: New

Construction and

Lamp

Replacement or

EL2 15.9 66W, 15.9lm/W & 3000hrs, Improved Halogen (Silver) 20.69 1.35 6.52 

Renovation New Lamp

Purchase EL3 17.5 60W, 17.5lm/W & 3000hrs, HIR 19.58 2.46 6.70 

EL4 19.1 55W, 19.1lm/W & 4000hrs, Improved HIR 18.98 3.06 8.02 EL5 20.3 51.7W, 20.3lm/W & 4200hrs, Improved HIR Plus 18.66 3.38 8.59 

8B­144

EE-2006-STD-0131 COMMENT 37.2
Table 8B.95 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Residential Sector using Hig

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 12.6 50W, 12.6lm/W & 3000hrs, Halogen 19.85 0.00 4.53 

47.8W, 13.2lm/W &

EL1 13.2 3000hrs, Improved Halogen 20.11 ­0.26 5.46 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 13.5 46W, 13.5lm/W & 6000hrs, Long Life HIR 17.60 2.25 6.09 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 14.0 45W, 14lm/W & 3000hrs, Improved Halogen (Silver) 19.71 0.14 5.92 

EL3 15.1 41.8W, 15.1lm/W & 3000hrs, HIR 18.90 0.95 6.09 EL4 17.0 40W, 17lm/W & 4000hrs, Improved HIR 18.14 1.71 7.41 EL5 19.1 40W, 19.1lm/W & 4200hrs, Improved HIR Plus 18.30 1.55 7.98 

8B­145

EE-2006-STD-0131 COMMENT 37.2
Table 8B.96 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Residential Sector using Low 

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 12.6 50W, 12.6lm/W & 3000hrs, Halogen 15.26 0.00 4.53 

47.8W, 13.2lm/W &

EL1 13.2 3000hrs, Improved Halogen 15.73 ­0.47 5.46 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 13.5 46W, 13.5lm/W & 6000hrs, Long Life HIR 14.69 0.57 6.09 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 14.0 45W, 14lm/W & 3000hrs, Improved Halogen (Silver) 15.58 ­0.32 5.92 

EL3 15.1 41.8W, 15.1lm/W & 3000hrs, HIR 15.07 0.20 6.09 

EL4 17.0 40W, 17lm/W & 4000hrs, Improved HIR 15.22 0.04 7.41 

EL5 19.1 40W, 19.1lm/W & 4200hrs, Improved HIR Plus 15.61 ­0.35 7.98 

8B.8.4 Electricity Price Trend Case Results

Because the LCC and PBP results for IRL are also highly dependent on electricity prices, DOE examined 

AEO2008 high and low growth electricity price trend cases. Chapter 8 describes the two cases and compares the

reference case electricity price trend. The following tables present the findings of the LCC and PBP analyses on 

baselines operating in the commercial and residential sectors, considering high and low growth cases. Key input

medium lamp prices, average operating hours in each sector, and an analysis period of 0.9 years in the commerci

years in the residential sector.

8B­146

EE-2006-STD-0131 COMMENT 37.2
Table 8B.97 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Commercial Sector under th

Growth Electricity Price Trend Case

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.6 90W, 14.6lm/W & 2500hrs, Halogen 34.57 0.00 6.20 

85.7W, 15.3lm/W &

EL1 15.3 2500hrs, Improved Halogen 34.56 0.00 7.14 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 15.9 82.5W, 15.9lm/W & 6000hrs, Long Life HIR 28.47 6.10 7.76 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 16.6 79W, 16.6lm/W & 3000hrs, Improved Halogen (Silver) 30.68 3.89 7.58 

EL3 18.0 70W, 18lm/W & 3000hrs, HIR 28.22 6.34 7.76 

EL4 19.8 66W, 19.8lm/W & 4000hrs, Improved HIR 26.25 8.31 9.08 

EL5 21.0 60W, 21lm/W & 4200hrs, Improved HIR Plus 24.93 9.63 9.65 

8B­147

EE-2006-STD-0131 COMMENT 37.2
Table 8B.98 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Residential Sector under th

Growth Electricity Price Trend Case

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.6 90W, 14.6lm/W & 2500hrs, Halogen 33.67 0.00 5.13 

85.7W, 15.3lm/W &

EL1 15.3 2500hrs, Improved Halogen 33.52 0.15 6.07 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 15.9 82.5W, 15.9lm/W & 6000hrs, Long Life HIR 28.93 4.74 6.70 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 16.6 79W, 16.6lm/W & 3000hrs, Improved Halogen (Silver) 30.54 3.13 6.52 

EL3 18.0 70W, 18lm/W & 3000hrs, HIR 27.98 5.69 6.70 

EL4 19.8 66W, 19.8lm/W & 4000hrs, Improved HIR 26.41 7.25 8.02 

EL5 21.0 60W, 21lm/W & 4200hrs, Improved HIR Plus 24.70 8.97 8.59 

8B­148

EE-2006-STD-0131 COMMENT 37.2
Table 8B.99 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Commercial Sector under th

Growth Electricity Price Trend Case

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.6 90W, 14.6lm/W & 2500hrs, Halogen 33.32 0.00 6.20 

85.7W, 15.3lm/W &

EL1 15.3 2500hrs, Improved Halogen 33.38 ­0.06 7.14 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 15.9 82.5W, 15.9lm/W & 6000hrs, Long Life HIR 27.33 6.00 7.76 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 16.6 79W, 16.6lm/W & 3000hrs, Improved Halogen (Silver) 29.59 3.73 7.58 

EL3 18.0 70W, 18lm/W & 3000hrs, HIR 27.26 6.06 7.76 

EL4 19.8 66W, 19.8lm/W & 4000hrs, Improved HIR 25.34 7.98 9.08 

EL5 21.0 60W, 21lm/W & 4200hrs, Improved HIR Plus 24.11 9.22 9.65 

8B­149

EE-2006-STD-0131 COMMENT 37.2
Table 8B.100 LCC and PBP Results for a 90W PAR38 Lamp Operating in the Residential Sector under th

Growth Electricity Price Trend Case

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.6 90W, 14.6lm/W & 2500hrs, Halogen 32.56 0.00 5.13 

85.7W, 15.3lm/W &

EL1 15.3 2500hrs, Improved Halogen 32.46 0.10 6.07 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 15.9 82.5W, 15.9lm/W & 6000hrs, Long Life HIR 27.91 4.64 6.70 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 16.6 79W, 16.6lm/W & 3000hrs, Improved Halogen (Silver) 29.56 3.00 6.52 

EL3 18.0 70W, 18lm/W & 3000hrs, HIR 27.11 5.45 6.70 

EL4 19.8 66W, 19.8lm/W & 4000hrs, Improved HIR 25.60 6.96 8.02 

EL5 21.0 60W, 21lm/W & 4200hrs, Improved HIR Plus 23.96 8.60 8.59 

8B­150

EE-2006-STD-0131 COMMENT 37.2
Table 8B.101 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Commercial Sector under 

Growth Electricity Price Trend Case

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.0 75W, 14lm/W & 2500hrs, Halogen 30.18 0.00 6.20 

71.7W, 14.6lm/W &

EL1 14.6 2500hrs, Improved Halogen 30.47 ­0.29 7.14 

(Xenon)

Event I: Lamp EL2 15.3 68.8W, 15.3lm/W & 6000hrs, Long Life HIR 24.46 5.72 7.76 

Failure; or Event

V: New

Construction and

Lamp

Replacement or

EL2 15.9 66W, 15.9lm/W & 3000hrs, Improved Halogen (Silver) 26.88 3.30 7.58 

Renovation New Lamp

Purchase EL3 17.5 60W, 17.5lm/W & 3000hrs, HIR 25.30 4.88 7.76 

EL4 19.1 55W, 19.1lm/W & 4000hrs, Improved HIR 23.04 7.14 9.08 EL5 20.3 51.7W, 20.3lm/W & 4200hrs, Improved HIR Plus 22.51 7.67 9.65 

8B­151

EE-2006-STD-0131 COMMENT 37.2
Table 8B.102 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Residential Sector under th

Growth Electricity Price Trend Case

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.0 75W, 14lm/W & 2500hrs, Halogen 29.11 0.00 5.13 

71.7W, 14.6lm/W &

EL1 14.6 2500hrs, Improved Halogen 29.26 ­0.15 6.07 

(Xenon)

Event I: Lamp EL2 15.3 68.8W, 15.3lm/W & 6000hrs, Long Life HIR 24.77 4.34 6.70 

Failure; or Event

V: New

Construction and

Lamp

Replacement or

EL2 15.9 66W, 15.9lm/W & 3000hrs, Improved Halogen (Silver) 26.58 2.52 6.52 

Renovation New Lamp

Purchase EL3 17.5 60W, 17.5lm/W & 3000hrs, HIR 24.94 4.17 6.70 

EL4 19.1 55W, 19.1lm/W & 4000hrs, Improved HIR 23.07 6.04 8.02 EL5 20.3 51.7W, 20.3lm/W & 4200hrs, Improved HIR Plus 22.18 6.93 8.59 

8B­152

EE-2006-STD-0131 COMMENT 37.2
Table 8B.103 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Commercial Sector under 

Growth Electricity Price Trend Case

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.0 75W, 14lm/W & 2500hrs, Halogen 29.15 0.00 6.20 

71.7W, 14.6lm/W &

EL1 14.6 2500hrs, Improved Halogen 29.48 ­0.33 7.14 

(Xenon)

Event I: Lamp EL2 15.3 68.8W, 15.3lm/W & 6000hrs, Long Life HIR 23.51 5.63 7.76 

Failure; or Event

V: New

Construction and

Lamp

Replacement or

EL2 15.9 66W, 15.9lm/W & 3000hrs, Improved Halogen (Silver) 25.97 3.18 7.58 

Renovation New Lamp

Purchase EL3 17.5 60W, 17.5lm/W & 3000hrs, HIR 24.47 4.67 7.76 

EL4 19.1 55W, 19.1lm/W & 4000hrs, Improved HIR 22.28 6.87 9.08 EL5 20.3 51.7W, 20.3lm/W & 4200hrs, Improved HIR Plus 21.80 7.35 9.65 

8B­153

EE-2006-STD-0131 COMMENT 37.2
Table 8B.104 LCC and PBP Results for a 75W PAR38 Lamp Operating in the Residential Sector under th

Growth Electricity Price Trend Case

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 14.0 75W, 14lm/W & 2500hrs, Halogen 28.18 0.00 5.13 

71.7W, 14.6lm/W &

EL1 14.6 2500hrs, Improved Halogen 28.38 ­0.19 6.07 

(Xenon)

Event I: Lamp EL2 15.3 68.8W, 15.3lm/W & 6000hrs, Long Life HIR 23.92 4.26 6.70 

Failure; or Event

V: New

Construction and

Lamp

Replacement or

EL2 15.9 66W, 15.9lm/W & 3000hrs, Improved Halogen (Silver) 25.77 2.41 6.52 

Renovation New Lamp

Purchase EL3 17.5 60W, 17.5lm/W & 3000hrs, HIR 24.20 3.99 6.70 

EL4 19.1 55W, 19.1lm/W & 4000hrs, Improved HIR 22.39 5.79 8.02 EL5 20.3 51.7W, 20.3lm/W & 4200hrs, Improved HIR Plus 21.54 6.65 8.59 

8B­154

EE-2006-STD-0131 COMMENT 37.2
Table 8B.105 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Commercial Sector under 

Growth Electricity Price Trend Case

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 12.6 50W, 12.6lm/W & 3000hrs, Halogen 20.21 0.00 5.59 

47.8W, 13.2lm/W &

EL1 13.2 3000hrs, Improved Halogen 20.50 ­0.29 6.53 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 13.5 46W, 13.5lm/W & 6000hrs, Long Life HIR 17.46 2.75 7.15 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 14.0 45W, 14lm/W & 3000hrs, Improved Halogen (Silver) 20.13 0.07 6.98 

EL3 15.1 41.8W, 15.1lm/W & 3000hrs, HIR 19.37 0.83 7.15 EL4 17.0 40W, 17lm/W & 4000hrs, Improved HIR 18.19 2.02 8.47 EL5 19.1 40W, 19.1lm/W & 4200hrs, Improved HIR Plus 18.62 1.58 9.04 

8B­155

EE-2006-STD-0131 COMMENT 37.2
Table 8B.106 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Residential Sector under th

Growth Electricity Price Trend Case

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 12.6 50W, 12.6lm/W & 3000hrs, Halogen 19.72 0.00 4.53 

47.8W, 13.2lm/W &

EL1 13.2 3000hrs, Improved Halogen 19.99 ­0.27 5.46 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 13.5 46W, 13.5lm/W & 6000hrs, Long Life HIR 17.49 2.24 6.09 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 14.0 45W, 14lm/W & 3000hrs, Improved Halogen (Silver) 19.59 0.13 5.92 

EL3 15.1 41.8W, 15.1lm/W & 3000hrs, HIR 18.80 0.93 6.09 EL4 17.0 40W, 17lm/W & 4000hrs, Improved HIR 18.03 1.69 7.41 EL5 19.1 40W, 19.1lm/W & 4200hrs, Improved HIR Plus 18.16 1.56 7.98 

8B­156

EE-2006-STD-0131 COMMENT 37.2
Table 8B.107 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Commercial Sector under 

Growth Electricity Price Trend Case

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 12.6 50W, 12.6lm/W & 3000hrs, Halogen 19.52 0.00 5.59 

47.8W, 13.2lm/W &

EL1 13.2 3000hrs, Improved Halogen 19.84 ­0.33 6.53 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 13.5 46W, 13.5lm/W & 6000hrs, Long Life HIR 16.82 2.70 7.15 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 14.0 45W, 14lm/W & 3000hrs, Improved Halogen (Silver) 19.51 0.00 6.98 

EL3 15.1 41.8W, 15.1lm/W & 3000hrs, HIR 18.80 0.72 7.15 EL4 17.0 40W, 17lm/W & 4000hrs, Improved HIR 17.64 1.88 8.47 EL5 19.1 40W, 19.1lm/W & 4200hrs, Improved HIR Plus 18.07 1.45 9.04 

8B­157

EE-2006-STD-0131 COMMENT 37.2
Table 8B.108 LCC and PBP Results for a 50W PAR30 Lamp Operating in the Residential Sector under th

Growth Electricity Price Trend Case

Event Response Efficacy Level Lamp Efficacy

lms/W

Lamp Option LCC

$

LCC Savings

$

Installed

Price

$

Op

Sa

(

Y

Baseline Baseline 12.6 50W, 12.6lm/W & 3000hrs, Halogen 19.11 0.00 4.53 

47.8W, 13.2lm/W &

EL1 13.2 3000hrs, Improved Halogen 19.41 ­0.30 5.46 

(Xenon)

Event I: Lamp

Failure; or Event

EL2 13.5 46W, 13.5lm/W & 6000hrs, Long Life HIR 16.92 2.19 6.09 

V: New

Construction and

Renovation

Lamp

Replacement or

New Lamp

Purchase

EL2 14.0 45W, 14lm/W & 3000hrs, Improved Halogen (Silver) 19.04 0.07 5.92 

EL3 15.1 41.8W, 15.1lm/W & 3000hrs, HIR 18.28 0.83 6.09 EL4 17.0 40W, 17lm/W & 4000hrs, Improved HIR 17.54 1.57 7.41 EL5 19.1 40W, 19.1lm/W & 4200hrs, Improved HIR Plus 17.67 1.44 7.98 

8B­158

EE-2006-STD-0131 COMMENT 37.2
REFERENCES

i U.S. Department of Energy, Office of Energy Efficiency and Renewable Energy. Energy Conservation Program 

Products: Final Report: U.S. Lighting Market Characterization, Volume I: National Lighting Inventory and Ene

Estimate. 2002. Washington, D.C.

< www.eere.energy.gov/buildings/info/documents/pdfs/lmc_vol1_final.pdf>

ii U.S. Department of Energy, Office of Energy Efficiency and Renewable Energy. Energy Conservation Program 

Products: Final Report: U.S. Lighting Market Characterization, Volume I: National Lighting Inventory and Ene

Estimate. 2002. Washington, D.C.

< www.eere.energy.gov/buildings/info/documents/pdfs/lmc_vol1_final.pdf>

8B­159

EE-2006-STD-0131 COMMENT 37.2