United States Environmental Protection Agency


# Technical Development Document for the Final Effluent Limitations Guidelines and New Source Performance Standards for the Airport Deicing Category

April 2012

## U.S. Environmental Protection Agency Office of Water (4303T) Engineering and Analysis Division

1200 Pennsylvania Avenue, NW Washington, DC 20460

EPA-821-R-12-005Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category

i 

## ACKNOWLEDGMENTS AND DISCLAIMER

This document was prepared by th e Environmental Protection Agency. Neither the United States Government nor any of its employees, contractors, subcontractors, or their employees makes any warranty, expressed or implied, or assumes any le gal liability or responsibility for any third party’s use of or the results of such use of any information, apparatus, product, or process discussed in this document, or represents that its use by such a party would not infringe on privately owned rights.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category

ii 

### CONTENTS

Page

1. L EGAL 

### A UTHORITY



### .............................................................................................................. 1 1.1 Clean Water Act ...................................................................................................... 1 1.1.1 Best Practicable Control Technology Currently Available (BPT) ............. 1 1.1.2 Best Conventional Pollutant Control Technology (BCT) ........................... 1 1.1.3 Best Available Technology Economically Achievable (BAT) ................... 1 1.1.4 New Source Performance Standards (NSPS) ............................................. 2 1.1.5 Pretreatment Standards for Existing Sources (PSES) ................................. 2 1.1.6 Pretreatment Standards for New Sources (PSNS) ...................................... 2 1.2 Effluent Guidelines Plan ......................................................................................... 3

2. A PPLICABILITY AND 

### S UBCATEGORIZATION



### ......................................................................... 4 2.1 Applicability of the Regulation ............................................................................... 4 2.2 Subcategorization .................................................................................................... 4 2.2.1 ADF Usage.................................................................................................. 4 2.2.2 FAA Classification...................................................................................... 5 2.2.3 Land Availability ........................................................................................ 5 2.2.4 Conclusions ................................................................................................. 5

3. D ATA 

### C OLLECTION 

### A CTIVITIES



### ........................................................................................... 6 3.1 Preliminary Data Summary ..................................................................................... 6 3.2 Site Visits ................................................................................................................ 6 3.3 Industry Questionnaires (Surveys) .......................................................................... 9 3.3.1 Recipient Selection and Qu estionnaire Distribution ................................... 9 3.3.2 Questionnaire Information Collected ........................................................ 11 3.3.3 Questionnaire Review, Codi ng, and Data Entry ....................................... 13 3.4 Field Sampling ...................................................................................................... 14 3.5 Permit Review ....................................................................................................... 14 3.5.1 Airport Selection for Permit Review ........................................................ 16 3.5.2 Obtaining NPDES Permits ........................................................................ 16 3.5.3 Permit Review Process ............................................................................. 16 3.6 Deicing Pad Costs ................................................................................................. 20 3.7 Industry-Submitted Data ....................................................................................... 20 3.8 Literature Reviews ................................................................................................ 22 3.8.1 Current Deicing Practices and Treatment Technologies .......................... 22 3.8.2 Current Airport Deicing Discharge Data .................................................. 23 3.8.3 Chemical Information and Environmental Impact Studies ....................... 23 3.8.4 Current Deicing Discharge Regulations ................................................... 23 3.9 Data Collected Based on Public Comments ......................................................... 24 3.9.1 EPA-Collected Data .................................................................................. 24 3.9.2 Data Submitted with Public Comments .................................................... 27 3.10 References ............................................................................................................. 27Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category



### CONTENTS (Continued)

Page

iii 

### 4. O VERVIEW OF THE 

### I NDUSTRY



### ............................................................................................ 28 4.1 Industry Statistics .................................................................................................. 28 4.1.1 Airports ..................................................................................................... 28 4.1.2 Airlines ...................................................................................................... 32 4.2 Industry Practices .................................................................................................. 34 4.2.1 Airfield Deicing Practices ......................................................................... 34 4.2.2 Aircraft Deicing Practices ......................................................................... 35 4.2.3 Airport Deicing Stormwater Collection and Control ................................ 38 4.2.4 Pollution Prevention Practices .................................................................. 39 4.3 References ............................................................................................................. 41

5. D EICING 

### C HEMICAL 

### U SE AND 

### D EICING 

### S TORMWATER 

### C HARACTERIZATION 

### ..................... 42 5.1 Deicing Chemical Usage ....................................................................................... 42 5.1.1 Airfield Chemical Use .............................................................................. 42 5.1.2 Aircraft Chemical Use and Purchasing Patterns ....................................... 43 5.2 Deicing Stormwater Characterization ................................................................... 43 5.2.1 Airfield Deicing Chemicals and A ssociated Deicing Stormwater ............ 44 5.2.2 Aircraft Deicing Chemicals and A ssociated Deicing Stormwater ............ 44 5.3 Aircraft and Airfield Deicing Chem ical Use and Associated Deicing Stormwater at Al askan Airports............................................................................ 53 5.4 References ............................................................................................................. 53

6. P OLLUTANTS OF 

### C ONCERN



### ................................................................................................ 55 6.1 Identification of Airport Deicing/An ti-icing Stormwater Pollutants .................... 55 6.2 Pollutants of Concern Selection Criteria............................................................... 61 6.3 Identification of Potential Pollutants of Concern .................................................. 61 6.4 Selection of Regulated Pollutants ......................................................................... 64 6.5 References ............................................................................................................. 66

7. C OLLECTION AND 

### T REATMENT 

### T ECHNOLOGIES 

### A PPLICABLE TO 

### A IRPORT 

### D EICING 

### O PERATIONS



### ...................................................................................................................... 68 7.1 Deicing Stormwater Collection ............................................................................. 68 7.1.1 Deicing Stormwater Coll ection and Conveyance ..................................... 68 7.1.2 Deicing Stormwater Storage ..................................................................... 72 7.2 Treatment .............................................................................................................. 74 7.2.1 Biological Treatment ................................................................................ 74 7.2.2 Physical Separation ................................................................................... 78 7.3 Recycling .............................................................................................................. 79 7.4 Pollution Prevention and Product Substitution Practices ...................................... 80 7.5 References ............................................................................................................. 86Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category



### CONTENTS (Continued)

Page

iv 

### 8. P ERFORMANCE OF 

### C ONTROL AND 

### T REATMENT 

### S CENARIOS 

### ............................................... 88 8.1 Deicing Pad Collection ......................................................................................... 88 8.2 Plug and Pump Collection with GCV ................................................................... 88 8.3 GCV Collection .................................................................................................... 89 8.4 AFB Treatment Performance ................................................................................ 89 8.5 References ............................................................................................................. 90

9. P OLLUTANT 

### L OADINGS AND 

### P OLLUTANT 

### L OAD 

### R EDUCTION 

### E STIMATES 

### .......................... 91 9.1 Data Sources ......................................................................................................... 91 9.2 Aircraft Deicing Pollutant Loading ...................................................................... 92 9.2.1 Estimate the Amount of Applied Deicing Chemical ................................ 92 9.2.2 Calculate the Amount of Pollutant Lo ad Associated with the Applied ADF......................................................................................................... 100 9.2.3 Estimate the Amount of Baseline Poll utant Load that is Discharged Directly ................................................................................................... 101 9.2.4 Estimate Pollutant Loading Discharges for Each ADF Collection/Control Scenario .................................................................... 102 9.2.5 Estimate Pollutant Loading Reductions for Each ADF Collection/Control Scenario .................................................................... 102 9.3 Airfield Deicing Pollutant Loading .................................................................... 107 9.3.1 Estimate the Amount of Applied Deicing Chemical .............................. 107 9.3.2 Calculate the Amount of Pollutant Lo ad Associated with the Applied Chemical ................................................................................................. 112 9.3.3 Estimate the Amount of Baseline Poll utant Load that is Discharged Directly ................................................................................................... 113 9.3.4 Estimate Pollutant Reductions for Each EPA Collection/Control Scenario................................................................................................... 113 9.4 References ........................................................................................................... 115

10. T ECHNOLOGY 

### C OSTS



### ....................................................................................................... 116 10.1 Costing Approach ............................................................................................... 116 10.2 Aircraft Deicing Costs ........................................................................................ 117 10.2.1 Overview of the ADF Collection and Treatment Airport Deicing Cost Model ...................................................................................................... 117 10.2.2 Airport Deicing Cost Model Equation Development ............................. 118 10.2.3 Development of Airport Deic ing Cost Model Inputs ............................. 128 10.2.4 Airport Deicing Cost Model Design ....................................................... 129 10.2.5 Annualized Costs for ADF Collection and Treatment Alternatives ....... 133 10.3 Airfield Deicing Costs ........................................................................................ 137 10.3.1 Urea and Potassium Acetate Chemical Costs and Application Rates ..... 137 10.3.2 Mechanical Application Equipment a nd Storage of Potassium Acetate 139Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category



### CONTENTS (Continued)

Page

v 

### 10.4 Other ADF-Compliance-Related Costs .............................................................. 142 10.4.1 Assessing ADF Usage from Airport Tenants ......................................... 143 10.4.2 Determination of ADF Stormwat er Collection Percentage .................... 143 10.4.3 Annual ADF Collection Equipment/System Inspections ....................... 146 10.4.4 COD Monitoring of On-Site Treatment Systems ................................... 147 10.5 Summary of Annualized Costs ........................................................................... 148 10.6 References ........................................................................................................... 153

11. R EGULATORY 

### O PTIONS 

### C ONSIDERED 

### A ND 

### S ELECTED 

### F OR BASIS 

### O F 

### F INAL 

### R EGULATION



### ............................................................................................................................... .......... 155 11.1 BPT and BCT ...................................................................................................... 155 11.2 BAT..................................................................................................................... 155 11.2.1 Airfield Deicing: Product Subs titution of Pavement Deicers Containing Urea ...................................................................................... 156 11.2.2 Aircraft Deicing: ADF Collect ion Requirements and Effluent Limitations .............................................................................................. 157 11.2.3 Options Considered for Today’s Fina l Regulation for Identification of BAT for ADF Collection and Discharge Requirements ......................... 158 11.2.4 BAT Options Selection ........................................................................... 159 11.3 NSPS ................................................................................................................... 160 11.4 PSES and PSNS .................................................................................................. 162 11.5 References ........................................................................................................... 162

12. N ON 

### -W ATER 

### Q UALITY 

### I MPACTS



### ..................................................................................... 164 12.1 Energy Requirements .......................................................................................... 164 12.2 Air Emissions ...................................................................................................... 166 12.2.1 Emissions from GCV Collection ............................................................ 166 12.2.2 Emissions from AFB Treatment Systems ............................................... 168 12.3 Solid Waste Generation ...................................................................................... 168 12.4 Summary ............................................................................................................. 169 12.5 References ........................................................................................................... 169

13. L IMITATIONS AND 

### S TANDARDS 

### : D ATA 

### S ELECTION AND 

### C ALCULATION 

### .......................... 171 13.1 Selected Pollutant Parameters ............................................................................. 171 13.1.1 COD ........................................................................................................ 171 13.1.2 Ammonia as Nitrogen (Ammonia) ......................................................... 171 13.2 Overview of Data Review and Selection ............................................................ 172 13.2.1 Data Selection Criteria ............................................................................ 172 13.2.2 Other Considerations in Data Selection .................................................. 174 13.3 Conventions for Modeling Multiple Data Sets from the Same Facility ............. 175 13.4 COD: Data Selected as Basi s of Final Limitations ............................................. 176 13.4.1 Albany Treatment System....................................................................... 176 13.4.2 COD Data from EPA Sampling Episode at Albany ............................... 177 13.4.3 COD Self-Monitoring Data from Albany Airport .................................. 178Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category



### CONTENTS (Continued)

Page

vi 

### 13.5 Ammonia: Data Selected as Basis of Final Limitation ....................................... 181 13.6 Limitations: Basis and Calculations.................................................................... 182 13.6.1 Definitions............................................................................................... 183 13.6.2 Percentile Basis of the Limitations ......................................................... 183 13.6.3 Estimation Procedures for Percentiles .................................................... 184 13.7 Achievability of Limitations ............................................................................... 187 13.7.1 Statistical and Engineering Review of Limitations ................................ 188 13.7.2 Compliance with Limitations .................................................................. 190 13.8 References ........................................................................................................... 192Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category

vii 

### LIST OF TABLES

Page

3-1 Airports V isited .......................................................................................................... ..........8

3-2 Deicing Questionnaire Response Rates .............................................................................10

3-3 Airports Selected for Sampling and the Reason for Their Selection .................................15

3-4 Top 50 Airports in the United States with the Highest ADF Usage, Estimated Based on SOFP Days and Total Airport Departures .........................................................17

3-5 Permit Review General Information Table ........................................................................19

3-6 Permit Review Pollutant-S pecific Information Table ........................................................20

3-7 Summary of Costing Da ta Provided by Industry ...............................................................21

3-8 Summary of Long-Term Analy tical Data Provided by Industry .......................................21

3-9 Selected Airport Information Re lated to Deicing Pad Operations .....................................25

4-1 Number of U.S. Airports by Airport Type in 2004 ............................................................29

4-2 Deicing Airports by FAA Region for the Three Winter Seasons ......................................30

4-3 Airline C lassifications ................................................................................................... .....33

4-4 National Estimate of Airports Us ing Deicing Chemical s or Materials ..............................35

4-5 Deicing/Anti-Icing Chemicals Purchase d by Airlines that Deiced Their Own Aircraft ...................................................................................................................... .........37

4-6 Deicing/Anti-Icing Chemicals Purcha sed for Aircraft Deiced by an FBO ........................37

4-7 Summary of Mechanical and Nonchemical Aircraft Deicing Methods Used by an Airline ....................................................................................................................... .........38

4-8 Summary of Mechanical and Nonchemi cal Aircraft Deicing Methods Used By FBOs .......................................................................................................................... ........38

4-9 Summary of Airport Collection, C ontainment, and Conveyance Methods .......................39

4-10 Summary of Airfield Poll ution Prevention Practices .........................................................40

4-11 Summary of Aircraft Poll ution Prevention Practices .........................................................40

5-1 U.S. Commercial Airports – National Estimate of Airfield Chemical Usage ...................42Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category



### LIST OF TABLES (Continued)

Page

viii 

### 5-2 U.S. Commercial Airpor ts – National Estimate of Aircraft Chemical Usage 1 

### .................43

5-3 EPA’s Analytical Results for Pond 3E Effluent and Pond 6 Effluent, DTW ....................45

5-4 MSP and DTW Grab Sample Data Summ ary for Collected Deicing Stormwater ............47

5-5 DEN, PIT, and ALB - 5-Day Averag e Data Summary for Untreated Deicing Stormwater .................................................................................................................... .....49

5-6 RFD - 1-Day Data Summary for Untreated Deicing Stormwater ......................................52

6-1 Pollutants Under Consideration as Potential Pollutants of Concern ..................................57

6-2 Potential Pollutants of Concern Selected for Regulation ...................................................65

7-1 ADF A lternatives .......................................................................................................... .....82

9-1 ADF Estimates Based on Airlin e Detailed Questionnaire Responses ...............................93

9-2 ADF Data Reported in th e Airport Questionnaire .............................................................95

9-3 ADF Annual Usage Estimates for In-scope Airports ........................................................97

9-4 Theoretical O xygen Demand Calculati ons for Aircraft Deicing Chemicals ...................100

9-5 ADF COD Baseline Loads and Loadi ng Reductions for Each Control and Treatment Scenario, by In-Scope Airport ........................................................................103

9-6 Three-Year Average Amount of Pavement Deicing Chemical Usage, in Pounds ..........108

9-7 ThOD Calculations for Ai rfield Deicing Chemicals .......................................................112

9-8 Baseline Ammonia and COD Load and Po tential Load Reduction Associated with the Discontinued Use of Urea as an Airf ield Deicing Chemical for In-Scope Airports ...................................................................................................................... ......114

10-1 GCV Capital and O&M Costs .........................................................................................121

10-2 Normalized Capital and O&M Costs fo r the Plug and Pump Collection System ...........122

10-3 Estimated Cost for 10,000 Linear Feet of Stormwater Piping .........................................124

10-4 Storage Tank Volumes and Installed Capital Cost for Various Airports .........................125

10-5 Normalized Annual O&M Costs for the AFB Reactors ..................................................127Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category



### LIST OF TABLES (Continued)

Page

ix 

### 10-6 Airport Deicing Cost Model Equations, Input Variables, and Assumptions ...................131

10-7 Annualized Costs by Model Facili ty for Control and Treatment ....................................134

10-8 Average Cost for Urea and Potassium Acetate, 2002-2005 ............................................138

10-9 Typical Application Rates for Potassium Acetate ...........................................................138

10-10 Application Rates for S odium Acetate and Urea .............................................................138

10-11 Cost for Application of Urea and Pota ssium Acetate, per 1000 Square Feet ..................139

10-12 Application Equipment Costs for Liquid Pavement Deicer ............................................140

10-13 Storage Tank Capital Costs for Liquid Pavement Deicer ................................................141

10-14 Annualized Costs for In-Scope Airpor ts to Change from Urea to Potassium Acetate for Airfield Deicing ............................................................................................142

10-15 Other C ompliance-Rela ted Costs by Airport ...................................................................144

10-16 Summary of EPA’s Annualized Costs fo r ADF Collection and Treatment, Airfield Deicing Urea Substitution, and Ot her Compliance-Related Costs ..................................149

11-1 Final Rule BAT Annualized Costs and Load Removals for In-Scope Airports ..............156

12-1 Potential Electricity Generati on from AFB Biogas Generation ......................................166

12-2 Estimated Incremental Pollutant Emissions from GCVs .................................................167

12-3 Potential Air Emissions fr om AFB Treatment Systems ..................................................168

12-4 Estimated Sludge Generation from AF B Bioreactors Treating ADF-Contaminated Stormwater .................................................................................................................... ...169

13-1 COD: EPA and Albany Air port Self-Monitoring Efflue nt Data Collected During EPA’s Sampling Episode .................................................................................................178

13-2 COD: Dates Excluded Because Units Operated in Series ...............................................179

13-3 COD: Dates Excluded Because Influe nt Concentration Reported as Zero ......................179

13-4 COD: Dates Excluded Because of Performance Excursions ...........................................180

13-5 COD: Summary of Albany Airport Self-Monitoring Effluent Data After Exclusions .................................................................................................................... ....181Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category



### LIST OF TABLES (Continued)

Page

x 

### 13-6 Ammonia: Data from Albany Airp ort Used to Develop Limitations ..............................182

13-7 COD and Ammonia: Final Limitations w ith Long-Term Averages and Variability Factors ....................................................................................................................... ......185

13-8 COD: 9 9 th 

### Percentile Estimates from Each Treatment Unit ............................................185

13-9 COD: Effect of Number of Da ily Values in Weekly Averages .......................................186

13-10 Ammonia: C onsideratio n of Autocorrelation for Fi nal Limitations, Long-Term Averages, and Variability Factors ....................................................................................187

13-11 COD: Dates and Values Greater than Final Limitation of 271 mg/L ..............................189

13-12 COD: Summary Statistics of Influent Concentrations .....................................................190Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category

xi 

### LIST OF FIGURES

Page

4-1 Percentage of Airports Deici ng Airfield Pavement Each Month .......................................31

4-2 Discharge Status of Airports .............................................................................................. 32

7-1 Deicing Pad Equipped with Fixed De icing Booms at Pittsburgh Airport .........................69

7-2 GCV

...................................................................................................................... ............71

7-3 Pond for Deicing Stormwater Storage ...............................................................................73

7-4 Frac T anks ................................................................................................................ ..........74

7-5 Aerated Pond Installatio n at Portland Airport ...................................................................76

7-6 Typical Anaerobic Fluid Bed Treat ment System for Treatment of ADFContaminated Stormwater .................................................................................................77

7-7 Infrared Hangar at JFK .................................................................................................... ..81

9-1 ADF Factor vs. PG/EG Gallons for U.S. Airports (excluding Alaska) .............................95

9-2 ADF Factor vs. PG/EG Gall ons for Alaskan Airports .......................................................96

10-1 AFB Reactor Capital Cost for Tr eating ADF-Contaminated Stormwater .......................126

13-1 Simplified Drawing of Albany Airport Treatment System and Sample Points ...............177Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 1 – Legal Authority

1 

### 1. L EGAL 

### A UTHORITY


### Effluent limitation guidelines and standard s for the Airport Deicing Category are promulgated under the authority of sectio ns 301, 304, 306, 307, 308, and 501 of the Clean Water Act, 33 U.S.C. 1311, 1314, 1316, 1317, 1318, and 1361.

1.1 Cl ean Water Act

Congress passed the Federal Water Pollution Control Act Amendments of 1972, also known as the Clean Water Act (CWA), to “resto re and maintain the chemical, physical, and biological integrity of the Nation’s waters” (section 101(a)). To implement the Act, the United States Environmental Protection Agency (EPA ) is to issue effluent limitation guidelines, pretreatment standards, and new source performance standards for industrial dischargers. These guidelines and standards are summarized briefly in the following sections.

1.1.1 Best Practicable Control Techno logy Currently Available (BPT)

Traditionally, EPA establishes BPT effluent limitations based on the average of the best performances of facilities within the industry, grouped to reflect various ages, sizes, processes, or other common characteristics. EPA may promulgate BPT effluent limits for conventional, toxic, and nonconventional pollutants. In specifying BPT, EPA looks at a number of factors. EPA first considers the cost of achieving e ffluent reductions in relation to the effluent reduction benefits. The Agency also considers the age of the e quipment and facilities, the processes employed, engineering aspects of the cont rol technologies, and required pro cess changes, non-water-quality environmental impacts (including energy requir ements), and such other factors as the Administrator deems appropriate. See CWA s ection 304(b)(1)(B)). If, however, existing performance is uniformly inadequate, EPA may es tablish limitations based on higher levels of control than are curren tly in place in an industrial category when based on an Agency determination that the technology is available in another category or s ubcategory, and can be practically applied.

1.1.2 Best Conventional Pollutant Control Technology (BCT)

The 1977 amendments to the CWA required EPA to identify additional levels of effluent reduction for conventional pollutants associated with BCT technology for discharges from existing industrial point sources. In addition to other factors sp ecified in section 304(b)(4)(B), the CWA requires that EPA establish BCT limitati ons after consideration of a two-part “costreasonableness” test. EPA expl ained its methodology for the development of BCT limitations in July 1986 (51 FR 24974). Section 30 4(a)(4) designates the following as conventional pollutants: biochemical oxygen demand over 5 days (BOD 5 

### ), total suspended solids (TSS), fecal coliform, pH, and any additional pollutants defined by the Administrator as conventional. The Administrator designated oil and grease as an additional conventional pollutant on July 30, 1979 (44 FR 44501; 40 CFR 401.16).

1.1.3 Best Available Technology Ec onomically Achievable (BAT)

BAT represents the second level of stringency for controllin g direct discharge of toxic and nonconventional pollutants. In general, BAT e ffluent limitation guidelines represent the best economically achievable performance of facilities in the industrial subcategory or category. TheTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 1 – Legal Authority

2 

### factors considered in assessing BAT include the cost of achieving BAT effluent reductions, the age of equipment and facilities involved, the process employed, potential process changes, and non-water quality environmental im pacts including energy requirem ents, and such other factors as the Administrator deems appropriate. The Agen cy retains considerable discretion in assigning the weight to be accorded these factors. An addi tional statutory factor considered in setting BAT is economic achievability. Generally, EPA dete rmines economic achievability based on total costs to the industry and the eff ect of compliance with BAT limita tions on overall industry and subcategory financial conditions. As with BPT, where existing performance is uniformly inadequate, BAT may reflect a hi gher level of performance than is currently being achieved based on technology transferred from a different subcategory or category. BAT may be based upon process changes or internal controls, ev en when these technologies are not common industry practice.

1.1.4 New Source Performance Standards (NSPS)

NSPS reflect effluent reducti ons that are achievable base d on the best available demonstrated control technology. New facilities have the opportunity to install the best and most efficient production processes and wastewater treatment technologies. As a result, NSPS should represent the most stringent cont rols attainable through the application of the best available demonstrated control technology for all polluta nts (i.e., conventional, nonconventional, and priority pollutants). In establis hing NSPS, EPA is directed to take into consideration the cost of achieving the effluent reduction and any non-water quality environmental impacts and energy requirements.

1.1.5 Pretreatment Standards for Existing Sources (PSES)

Pretreatment standards apply to discharges of pollutants to publicly owned treatment works (POTWs) rather than to discharges to wa ters of the United States. PSES are designed to prevent the discharge of pollutants that pa ss through, interf ere with, or are otherwise incompatible with the operation of POTWs. Ca tegorical pretreatment standards are technologybased and analogous to BAT effluent limitati on guidelines. The Ge neral Pretreatment Regulations, which set forth the framework for th e implementation of categorical pretreatment standards, are found at 40 CFR Part 403. These regul ations establish pretreatment standards that apply to all nondomestic discharger s. See 52 FR 1586 (January 14, 1987).

1.1 .6 Pretreatment Standards for New Sources (PSNS)

Section 307(c) of the Act calls for EPA to promulgate PSNS at the same time it promulgates NSPS. Such pretreatment standards mu st prevent the discharge of any pollutant into a POTW that may interfere with, pass through, or may otherwise be incompatible with the POTW. EPA promulgates categorical PSES base d principally on BAT technology for existing sources. EPA promulgates PSNS based on best available demonstrated technology for new sources. New indirect discharges have the opportunity to incorporate into th eir facilities the best available demonstrated technologies. The Agency considers the same factors in promulgating PSNS as it considers in promulgating NSPS.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 1 – Legal Authority

3 

### 1. 2 Effluent Guidelines Plan

In 2004, EPA issued its biannual effluent guidelines plan under section 304(m) of the CWA. This plan announced the initiation of rule making for the Airport Deicing Category (69 FR 53705, September 2, 2004).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 2 – Applicability and Subcategorization

4 

### 2. A PPLICABILITY AND 

### S UBCATEGORIZATION


### This document presents the information and rationale supporting the effluent limitation guidelines and standards for the Airport Deicing Category. Section 2 highlights the applicability and subcategorization basi s of this regulation.

2 .1 Applicability of the Regulation

Airports in the scope of this regulation are defined as Primary Comm ercial Airports that conduct deicing activities.

2 .2 Subcategorization

The CWA requires EPA to consider a numbe r of different factors when developing effluent limitation guidelines. For example, when developing limitations that represent the BAT for a particular industrial categ ory, EPA must consider among othe r factors the following: the age of the equipment and facili ties in the category, location, manufacturi ng processes employed, types of treatment technology to reduce the effluent discharges, costs of e ffluent reductions, and non-water-quality impacts (CWA section 304(b)(2)(B)). The statute also allo ws EPA to take into account other factors that the EPA Administrato r deems appropriate and requires the BAT model technology chosen by EPA to be economically achie vable, which generally involves considering both compliance costs and overall fi nancial condition of the industry.

For this rulemaking, EPA evaluated the character istics of the Airport Deicing Category to determine their potential to provide the Agency w ith a means to differentiate effluent quantity and quality among facilities. EPA also eval uated the design, process, and operational characteristics of the different industry segments to determin e technology control options that might be applied to reduce effluent quantity and improve effluent quality. Based on this analysis, below are the factors that EPA evaluated to determine whether subcategorizing the Airport Decicing Category would be appropriate:

• 

### Aircraft deicing fluid (ADF) usage;

• 

### Fede ral Aviation Administrati on (FAA) classifications; and

• 

### Land availability.

2.2.1 ADF Usage

Ethylene glycols (EG) and pr opylene glycols (PG) are the main ingredients in ADF. Through EPA’s research, it became a pparent that the volume of glycol required to deice a single aircraft varied greatly depending on a number of variables including weathe r conditions, aircraft size, and operator training. EPA reviewed industry questionnaire responses and determined that ADF usage is the best indicator for the volume of deicing operations that occur at an airport. ADF usage can range from zero to hundreds of thous ands of gallons per year at airports across the United States.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 2 – Applicability and Subcategorization

5 

### 2.2.2 FAA Classification

The Airport and Airway Improvement Act (AAI A) and the FAA classify airports by size based on the volume of commercial traffic. (Noncommercial airports, commonly known as "General Aviation" airports, are not specifically defined by the AAIA.) EPA utilized this classification system to organize its data collection and analys is of the aviation industry. The AAIA defines airports by categories of airport ac tivities, including Commercial Service (Primary and Nonprimary), Cargo Service, and Reliever. Commercial Servi ce Airports are publicly owned airports that have at least 2,500 passenger boardings each calenda r year and receive scheduled passenger service. The definition also includes passengers who continue on an aircraft in international flight that stops at an airport in any of the 50 states for a nontraffic purpose, such as refueling or aircraft maintenance rather than passenger activity. Primary Commercial Service airports have more than 10,000 passenger board ings each year. Primary Commercial Service airports are further subdivided into La rge Hub, Medium Hub, Small Hub, and Non-hub classifications, based on the per centage of total passenger boardings within the United States in the most current calendar year ending befo re the start of the current fiscal year.

Early in the regulatory process, EPA assumed that the majority of the deicing in the United States would occur at Prim ary Commercial Service airports and particularly those with nonpropeller departures. General aviation aircraft, as well as smaller commercial propeller driven aircraft are expected to suspend fli ghts during inclement weat her, whereas commercial aircraft with scheduled service are much more likely to deice to meet customer demands.

2. 2.3 Land Availability

EPA is aware that airports across the country have different amounts of land that may be available for facility modifications, such as installing environmental controls. EPA collected some basic information from airports on their current configurations. However, neither the aviation industry nor the FAA has developed a standard definition of land availability.

As part of the public comments on the propos ed rule, commenters requested that EPA subcategorize airports that woul d be prohibited from installing deic ing pads due to gate, runway, and taxiway space constraints and lack of available land. EPA did not set a spent ADF collection requirement as part of BAT in the final rule a nd therefore did not separa te these airports into their own subcategory.

2.2 .4 Conclusions

EPA concludes that establishing formal sub categories is not necessary for the Airport Deicing Category; rather, EPA structured the applicability of the final rule to address the relevant factors and established a set of requirements that encompasses the range of situations that an airport may encounter during deicing operations.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

6 

### 3

. D ATA 

### C OLLECTION 

### A CTIVITIES


### To characterize airport deicing operations and to develop the fi nal effluent limitation guidelines and standards, EPA collected and ev aluated technical and economic data from a variety of sources. This section describes the following data sources used for the Airport Deicing Category rulemaking effort:

Section 3.1 – Preliminary Data Summary Section 3.2 – Site Visits Section 3.3 – Industry Questionnaires (Surveys) Section 3.4 – Field Sampling Section 3.5 – Permit Review Section 3.6 – Deicing Pad Costs Section 3.7 – Industry-Supplied Data Section 3.8 – Literature Reviews Section 3.9 – Data Collected as Part of Public Comments

3 .1 Preliminary Data Summary

EPA’s initial source of wastew ater discharge information fo r the aviation industry was the Preliminary Data Summary (PDS): Airport Deicing Operations, which was published in August 2000 (USEPA, 2000). This study focused on approximately 200 U.S. airports with potentially significant deicing/anti-icing operations. For the study, EPA collected information from industry questionnaires, engi neering site visits, wastewater sampling activities, meetings with industry and regulatory agencies, and technical and scientific litera ture. See Section 3.0 of the PDS for detailed information on th e study’s data colle ction activ ities.

The questionnaires that EPA reviewed incl uded the 1993 Screener Questionnaire for the Transportation Equipment Cleani ng Industry and a set of questi onnaires distributed during the study to major and regional airports and airlines, technology vendors, and POTWs.

From September 1997 through March 1999, the Ag ency conducted 16 airport site visits and six sampling episodes to colle ct information about deicing pro cesses, deicing equipment, and deicing wastewater generation, collection, handling, and treatment technologies.

EPA met with the FAA, deicing fluid manufact urers and formulators, airlines, industry associations, technology vendors, and other interested parties to discuss environmental and operational issues related to aircraft deicing and anti- icing operations.

Literature searches provided information on th e toxicity, industry usage, and mitigation techniques for ADFs. The literature also covered topics such as alternative fluid types, pollution prevention practices, economic and financ ial data, and environmental impacts.

3 .2 Site Visits

Between December 2004 and November 2005, EPA conducted 20 airport site visits to collect current information about aircraft and airfield deicing practices , deicing equipment, deicing stormwater generation, co llection, handling, and control. Du ring these site visits, EPA also evaluated potential sampling locations for the sampling program described in Section 3.4.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

7 

### EPA used information collected from the PD S, updated airport lite rature searches, and other Agency-supplied data to a ssess potential airports for si te visits. EPA also solicited recommendations from industry trade associatio ns, including the Air Transport Association (ATA), the American Association of Air line Executives (AAAE) and Airports Council International-North America (ACI-NA). EPA co nsidered the following criteria in evaluating which airports to visit:

• 

### Hub size and location of the airport;

• 

### ADF handling practices;

• 

### Deicing stormwater collecti on and control practices; and

• 

### ADF-contaminated stormwater discharge practices.

In general, EPA visited Me dium Hub and Large Hub air ports operating in northern climates that conduct aircraft and airfield deicin g operations each winter. EPA also visited some Small Hub airports to evaluate potential issues related to an ai rport’s size. The Agency visited airports that use a vari ety of deicing practices (such as ga te deicing, centralized deicing pads (CDPs), deicing trucks and st ationary booms, infrared deicin g hangars) and various deicing stormwater collection and contro l technologies (such as dedicated deicing stormwater collection systems, stormwater treatment through biologica l systems, and glycol recovery systems). Table 3-1 lists the 20 airports visited in 2004 and 2005, the visit dates, and EPA’s rationale for selecting each for a site visit. This table also lists a post-proposal site visit conducted at Boston Logan airport.

During the site visits, EPA collected the following information:

• 

### General airport and deicing operations in formation, including size and age of the airport, permit status, information on the entities that perform deicing operations (both aircraft and airfield), and cu rrent airline tenant information;

• 

### Description of the deicing/ anti-icing operations conducted at the airport, including the types of equipment used, locations of deicing operations, and information on any pollution prevention or “s tate-of-the-art” systems in use at the airport that improved their deicing operations;

• 

### De icing chemicals used, including ADF type (e.g., Type I-IV), pavement deicer type, and any chemical usage information available;

• 

### Desc ription of the deicing stormwater co llection and control systems used at the airport, including any glycol recovery or stormwater treatment systems and their effectiveness and any available cost information for these systems; and

• 

### Airpor t monitoring and discharge of de icing stormwater, including pollutants monitored and frequency of monitoring.

This information is documented in the Site Visit Report (SVR) for each airport visited.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

8 

### Table 3-1. Airports Visited

Airport Name Airport Code Date of Visit Airport Details Washington Dulles International IAD 12/1/2004 Local Large Hub airport, ADF-contaminated stormwater collection and glycol recovery, indirect discharger Baltimore-Washington International BWI 12/15/2004 Local Large Hub airport, deicing pads, ADFcontaminated stormwater collection, indirect discharger Chicago O’Hare International ORD 1/26/2005 Large Hub airport, ADF-contaminat ed stormwater collection with indirect discharge, upgrades to system since the PDS site visit
General Mitchell International (Milwaukee) MKE 1/27/2005 Medium Hub airport, ADF-contaminated stormwater collection and indirect discharge, extensive monitoring data in collaboration with U.S. Geological Survey (USGS) Detroit Metropolitan Wayne County DTW 1/28/2005 Large Hub airport, deicing pads, ADF-contaminated stormwater collection with glycol recovery, both direct and indirect discharger Ronald Reagan Washington National DCA 2/1/2005 Local Large Hub airport, changes in ADF practices since PDS site visit, ADF- contaminated stormwater collection Syracuse Hancock International SYR 2/9/2005 Small Hub airport, deicing pads, aerated stormwater lagoons, indirect discharger Albany International ALB 2/10/2005 Small Hu b airport, ADF-contam inated stormwater collection with anaerobic an d aerobic treatment, direct discharger, upgrades to system since PDS site visit Pittsburgh International PIT 2/10/2005 Large Hub airport, deicing pads, glycol recovery andtreatment (ultra filtration and reverse osmosis) of ADFcontaminated stormwater , direct discharger
Cincinnati/Northern Kentucky International CVG 2/11/2005 Large Hub airport, variety of ADF-contaminated stormwater-related activities, recommended by FAA as a site visit location, on-site aerobic treatment, direct and indirect discharger
Richmond International RIC 2/16/2005 Local Small Hub airport Minneapolis/St. PaulInternational/WorldChamberlain MSP 2/18/2005 Large Hub airport, ADF collection with glycol recovery, direct and indirect discharger

James M Cox Dayton International DAY 2/25/2006 Small Hub airport, centralized deicing with ADFcontaminated stormwater collection
Portland International (Oregon) PDX 7/26/2005 Medium Hub northwestern airport, indirectly discharges high-strength deicing stormwater, sends low-strength deicing stormwater to detention pond and then to direct discharge
Seattle-Tacoma International SEA 7/27/2006 Large Hub northwestern airport, industrial stormwater treatment on site LaGuardia (New York) LGA 10/11/2005 Large Hub airport, direct discharger, part of New York City area visitsTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities


### Table 3-1 (Continued)

9 Airport Name Airport Code Date of Visit Airport Details John F. Kennedy International (New York) JFK 10/11/2005 Large Hub airport with a high percentage of international flights, direct discharger, part of New York City area visits, future plans for infrared deicing Newark Liberty International EWR 10/12/2005 Large Hub airport, infrared deicing technology since 1999 Salt Lake City International SLC 11/8/2005 Large Hub western airport, ADF-contaminated stormwater collection with glycol recovery
Denver International DEN 11/9/2005 Large Hub western airport, deicing pads, ADFcontaminated stormwater collection with glycol
recovery General Edward Lawrence Logan International BOS 3/21/2011 Space-constrained ai rport with no ADF-contaminated stormwater collection and direct discharge



### 3.3 Indu stry Questionnaires (Surveys)

EPA distributed three questionnaires to dir ectly support the Airport Deicing rulemaking. Section 3.3.1 discusses the recipi ent selection process, distribu tion, and mail-out results for the three airport deicing questionnair es. Section 3.3.2 discusses the organization of and type of technical information request ed in each questionnaire.

3 .3.1 Recipient Selection and Questionnaire Distribution

EPA distributed a screener questionnaire foll owed by a detailed airline questionnaire to airlines, and a questionnaire to airports. The overall focus of the questionnaires was on airports and airlines that perform deic ing and anti-icing on aircraft and/or airfield pavement. EPA selected airports for the airport questionnair e by airport type (i.e., Large Hub, Medium Hub, Small Hub, and Non-hub), days and amount of snow or freezing precipitati on, and the number of departures. EPA performed a census design for large and Medium Hub 1 

### airports and a stratified random sample design for small and Non-hub airports (see the Statistical Support Memorandum DCN AD01208).

EPA selected recipients for the airline screen er questionnaire by identifying airlines with greater than 1,000 departures per ye ar at those airports selected for the airport questionnaire. EPA selected airlines for the detailed air line questionnaire based on the airline screener questionnaire responses (which id entified whether an airline dei ced its aircraft or used some other entity) at the specified airports. To reduce respondent bu rden, EPA asked the selected

1 FAA classifies large commercial airports into size categories of “hubs,” based on the number of annual enplanements that occur at the airpor t. Enplanements represent the number of passengers boarding the plane for departure. Large Hubs are airports that represent more than 1 percent of total U.S. passenger enplanements. Medium Hubs are airports that account for more than 0.25 percent but less than 1 percent of total passenger enplanements. Small Hubs enplane 0.05 to 0.25 percent of the total passenger enplanements. Airports with less than 0.05 percent of the total passenger enplanements but more than 10,000 annual enplanements are co nsidered Non-hub primary airports.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

10 

### airlines to provide data on a limited subset of the airports they served for which they were expected to use the maximum am ount of deicing chemicals.

Table 3-2 summarizes the number of questionnaires distributed in each category and their response rates.

Table 3-2. Deicing Questionnaire Response Rates

Questionnaire Type Distributed Returned Undelivered Returned Completed Not Returned Airport Deicing Questionnaire 153 0 (0%) 150 (98%) 3 (2%) 1 Airline Screener Questionnaire 2 72 1 (1%) 70 (97%) 1 (1%) Airline Deicing Detailed Questionnaire 58 0 (0%) 49 (84%) 9 (16%)

1 EPA determined that one airport recipient was out of scope and removed it from the sample frame.
2 Information was collected from an additional 22 foreign carriers.



### 3 .3.1.1 Airport Questionnaire

EPA selected 153 airports to receive the airport questionnaire and distributed the questionnaire to these airports in April 2006. Of the 153 airport questionnaires distributed, 150 were completed and returned. EPA removed one of the three nonrespondent airports from the sample frame because it was a c ity airport operating as a tenant at a military airport. EPA determined that its selection was based on data for the military airport operations, not the city airport, and military airports were not included in the sample frame.

3 .3.1.2 Airline Screener Questionnaire

EPA initially selected 72 airlines as recipients of the screener questionnaire. The recipient group comprised a random sample of airlines with greater than 1,000 departures per year operating at the airports selected for the ai rport questionnaire. In April 2006, the Agency distributed the airline screener questionnaire to the 72 airlines. EP A also identified 22 additional foreign airlines for which information would be us eful in developing effluent guidelines, but that were not captured by the random sample. EPA collected aircraft deicing and anti-icing information for these 22 foreign carriers through contacts with airport managers where the carriers operated.

Of the 72 screener questionnaires distribute d, 70 were completed and returned to EPA. Of the two not returned, one questionnaire was returned undelivered, as the airline had ceased operations.

3.3.1 .3 Airline Detailed Questionnaire

Using the responses from the airline screen er questionnaire, EPA selected and sent a more detailed questionnaire to 58 airlines that responded they deice planes at any of the airports that received an airport questionnaire. This questionnaire was distributed in March 2007. The selection included 448 airline/air port combinations. The Agency cat egorized the airline/airport combinations according to the entity that pe rformed most of the deicing for the 2002/2003, 2003/2004, and 2004/2005 winter seasons as listed below:Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

11 

### • 

### Airlin e/airport combinations that deice their own aircraft;

• 

### Airlin e/airport combinations that contra ct to fixed-base operators (FBOs) for deicing services; or

• 

### Airlin e/airport combinations that contract to other airlines for deicing services.

Of the 58 airline detailed ques tionnaires sent, 49 were comple ted returned and nine were not returned.

3 .3.2 Questionnaire Information Collected

EPA designed the questionnaires to collect curr ent information with sufficient detail to support development of effluent guidelines. The questionnaires collected information on deicing operations performed on aircraft and airfield pavement, includi ng deicing stormwater generation, collection, characterization, mana gement, and treatment. The airline screener supported the selection of recipients for the ai rline detailed questionnaire. This section describes the technical information collected and the purpose of each of the three questionnaires.

3 .3.2.1 Airport Questionnaire

EPA divided the airport deicing questionnair e into the following pa rts and sections:

PART A: TECHNICAL INFORMATION

Section 1: General Airport Information Section 2: Airport Deicing and Anti-Icing Operations Section 3: Deicing Stormwater Containment and/or Collection Section 4: Deicing Stormwater Treatment/Recovery Section 5: Analytical Data Section 6: Pollution Prevention Practices

PART B: FINANCIAL AND ECONOMIC INFORMATION

Section 1: Ownership and Management Structure Section 2: Airport Finances Section 3: Capital Expenditures Section 4: Airport Operations

Part A, Section 1 (Questions 1 through 24) re quested information to identify the airport and primary contacts, to confirm that aircraft deicing/anti-icing was pe rformed during the three designated winter seasons (2002/2003, 2003/2004, and 2004/2005), and to characterize deicing operations. This information includ ed the destination of deicing/ anti-icing stormwater, receiving surface waters, the entity that performed aircraft and/or airf ield pavement deicing, and the number of deicing/anti-icing da ys per winter season. This info rmation helped EPA update the industry profile on airports deicing in the U.S ., characterize deicing/an ti-icing operations, and determine the proximity and types of eco systems within and beyond airport boundaries

Part A, Section 2 (Questions 25 through 31) requested detailed info rmation about airport deicing/anti-icing stormwater s ources, flows, and destinations as well as deicing/anti-Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

12 

### icingchemicals, materials, and practices. EPA us ed this information to develop an industry profile of deicing stormwater generation and collection, to dete rmine baseline loadings using airfield deicing chemical usage, and to deve lop and evaluate possibl e regulatory technology options and compliance cost estimates.

Part A, Section 3 (Questions 32 through 39) requested information on the collection, containment, conveyance, discharge and/or di sposal methods for deicing stormwater, and pollution prevention and best management practices . EPA used this information to develop an industry profile of deicing stormwater coll ection/containment/conveyance methods and to evaluate pollution prevention and best management practices.

Part A, Section 4 (Questions 40 through 51) requested information on deicing stormwater treatment technologies and units operated by the airport, including deicing stormwater treatment diagrams, design and operating specifications, sources of wastewater influent, treatment chemical additions, treatment operations and ma intenance costs, and discharge practices. EPA used this information to develop control tec hnology options, regulatory options, and compliance cost estimates.

Part A, Section 5 (Questions 52 through 55) requested information concerning the availability of deicing stormw ater characterization data, recei ving water in-stream monitoring data, and/or data characterizing the effectivene ss of treatment of deicing stormwater. EPA used this information to follow up with selected airports to request long-term monitoring data, to estimate pollutant discharge loadings, to character ize behavior of the disc harge in the receiving water, to assess deicing stormwater treatment t echnologies, and to assess environmental impacts.

Part A, Section 6 (Questions 56 through 68) re quested information to evaluate the status of pollution prevention practices at each airport and to identif y pollution prevention technologies. EPA used this information to iden tify appropriate practices as regulatory options and to prepare an industry profile of pollution prevention practices.

Part B of the questionnaire requested ai rport financial and economic information. Section 1 requested information on the ownership and management structure that EPA used to develop the industry profile and to estimate economic impacts of an effluent guideline. Section 2 requested information on operation fi nances that EPA used to projec t the potential impacts of the rule. Section 3 requested information on current capital airport expenditures that EPA used to assess the capability of airpor ts to pay for deicing-related capital improvements. Section 4 requested information on the finances for airpor t operations, including th e airport’s financial statement, which EPA used to determ ine the airport’s cost of capital.

3 .3.2.2 Airline Screener Questionnaire

The airline screener questionnaire included three questions. Question 1 requested the contact information for the airline should EPA need to verify or clarify their response. Question 2 asked who (the airline, anothe r airline, FBO, or private cont ractor) performed most of the deicing/anti-icing on the respondent ’s aircraft at specific airp orts. Question 3 provided an opportunity for the respondent to provide addi tional information or comment on its responses. EPA used this information to identify potential ai rline detailed questionnaire recipients and to indicate the potential co ntribution of FBOs to deicing opera tions and to the discharge of ADFcontaminated stormwater.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

13 

### 3 .3.2.3 Airline Detailed Questionnaire

EPA divided the airline detailed questionna ire into the following parts and sections:

PART A: TECHNICAL INFORMATION

Section 1: General Airline Information Section 2: Airline Deicing and Anti-Icing Operations (at each airport specified in Section 1) Section 3: Pollution Prevention Practices (at each airport specified in Section 1)

PART B: DEICING COSTS AND OPERATIONS

Section 1: Airline Deicing Costs and Operations Section 2: Airport-Specific Deicing Costs and Operations

Part A, Section 1 (Questions 1 through 4) re quested verification of the airline name and address and identification of the primary and seconda ry contacts to clarify or verify the technical questionnaire responses.

Part A, Section 2 (Questions 5 through 18) requested information on deicing/anti-icing operations performed by the airline or for the air line at each specified airport. The Agency used this information to:

• 

### Develop an industry profile of ADF usag e and deicing stormwater generation;

• 

### Estimate pollutant loadings;

• 

### Char acterize deic ing stormwater;

• 

### Ev aluate differences in airport deicing st ormwater generation and characteristics;

• 

### Identify pollutants of concern; and

• 

### Identify opportunities for pollution prevention through chemical substitution and best management practices.

Part A, Section 3 (Questions 19 through 31) requested information on the airline’s pollution prevention practices including a descri ption of each practice and any costs and/or savings from its implementation. The Agency eval uated this information to identify appropriate practices that could become pa rt of regulatory options and to develop an industry profile.

Part B of the questionnaire requested ai rline financial and economic information. Section 1 requested information on ownership, ai rcraft deicing costs and operations, and the airline’s financial statement, that EPA used to develop the industry economic profile and to conduct the economic analysis. Section 2 request ed detailed information regarding airlinespecific deicing costs and operations at specific airport locations. The Agency also used this information for the industry economic profile and to determine the economic impacts of the rule.

3 .3.3 Questionnaire Review, Coding, and Data Entry

EPA reviewed the screener and the two de tailed questionnaires for completeness, accuracy, and consistency of the responses. In some cases, the Agency followed up with the airport or airline by email or te lephone to clarify responses or to obtain missing or incompleteTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

14 

### information. During the review, EPA coded responses to facilitate entry of data into the airline screener and the airline and ai rport questionnaire databases.

The Agency developed databases containing the information provided by questionnaire respondents of each questionnaire. After detailed review and codi ng, EPA entered data from the questionnaires into the appropriate database us ing a double-key-entry and verification procedure to identify and resolve differences between the two data entry tasks.

3.4 Field Sampling

EPA conducted sampling episodes at six airports from March 2005 through August 2006 to characterize ADF and ADF-contaminated stormw ater discharges and to evaluate treatment technologies for stormwater affect ed by aircraft and airfield deic ing practices. EPA used existing industry profile information and information collected during airport site visits to determine the most appropriate locations for sampling. The Agency evaluated the following criteria for selecting sampling sites:

• 

### S ize and location of the airport;

• 

### D eicing stormwater collecti on and control practices; and

• 

### A DF-contaminated stormwater discharge practices.

EPA conducted the episodes to characteri ze deicing stormwater and assess the capabilities and effectiveness of several different treatment technologies such as anaerobic treatment, aerobic treatment, distillation, reve rse osmosis, mechanical vapor recompression, aeration, and chemical addition. Table 3-3 lists the airports selected for EPA sampling, the reason for selection, and the points that were sampled.

3 .5 Permit Review

During the regulatory development process, EPA reviewed National Pollutant Discharge Elimination System (NPDES) permits to unders tand what permit authorities are currently requiring of airports with respec t to deicing stormwater control. Using the data gathered during the permit review assisted EPA in:

1

. Assessing the current state of deicing stormwater control; 2

. Evaluating the effectiveness of various de icing stormwater cont rol measures; and 3

. Identifying potential measures that EP A could use to furt her control deicing
stormwater.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

15 

### Table 3-3. Airports Selected for Samplin g and the Reason for Their Selection

Airport Name Airport Code Dates of Sampling Reason for Sampling Sample Points Detroit Metropolitan Wayne County Detroit, MI Episode 6508 DTW 3/31/05 Collects highly concentrated ADF for recycling, significant stormwater volumes, direct and indirect discharger • Untreated deicing stormwater

• Effluent from ADF-contaminated stormwater collection pond

• Effluent from pavement deicer stormwater collection pond

• ADF, as applied

• Quality control (QC) samples 1 Minneapolis/St. Paul International Minneapolis/St. Paul, MN Episode 6509 MSP 4/28/05 On-site collection and recycling facility, direct and indirect discharger • High concentration ADFcontaminated stormwater storage tank

• Low concentration ADFcontaminated stormwater storage tank

• Influent to pavement deicer stormwater collection pond

• Effluent from pavement deicer stormwater collection pond

• ADF, as applied

• QC samples 1 Albany International Albany, NY Episode 6523 ALB 2/5/06- 2/10/06 Reported recovery efficiency of 72% of applied ADF through collection and treatment (anaerobic and aerobic) of ADF-contaminated
stormwater • Influent to anaerobic treatment

• Effluent from anaerobic treatment

• Effluent from aerobic treatment

• QC samples 1

Pittsburgh International Pittsburgh, PA Episode 6528 PIT 2/26/06- 3/3/06 Reported recovery efficiency of 60-66% of applied ADF through collection and treatment (ultrafiltration and reverse osmosis (RO)) of ADF-contaminated
stormwater • Influent to RO treatment

• Effluent from RO treatment

• QC samples 1

Denver International Denver, CO Episode 6522 DEN 3/26/06- 3/31/06 ADF-contaminated stormwater collection with glycol recovery • Influent to mechanical vapor recompressions (MVRs)

• Influent to distillation column

• Distillate from MVRs

• Overhead from distillation column

• Effluent from treatment

• QC samples 1

Greater Rockford Rockford, IL Episode 6529 and 6530 RFD 4/20/06 and 8/29/06 On-site aerated lagoon treatment system (run in batch mode) for its deicing-contaminated
stormwater Spring Sampling

• Infl uent to aerobic pond treatment

• QC sa mples 1 Summer Sampling

• Effl uent from aerobic pond
treatment

• QC samples 1Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

16 

### 3 .5.1 Airport Selection for Permit Review

For this review, EPA selected the top 50 U.S. airports based on ADF usage. At the time of review, usage estimates from the airline survey were not available; therefore, EPA estimated the airports with the highest usage using a “w eighting factor” based on the number of snow or freezing precipitation (SOFP) days and commercial departures as a measure of ADF usage. Table 3-4 displays the results of the weighting factor analysis and lists the 50 airports for which EPA reviewed permits.

3 .5.2 Obtaining NPDES Permits

From the list of selected airports for perm it review, EPA identified those for which it already had permits. While airpor ts were not required to subm it permits as part of their questionnaire response, some ai rports did so. Furthermore, there were some permits already available in the airport deicing r ecord files. Therefore, as a fi rst step, EPA reviewed available documentation and survey responses to identify in-house permit availability.

As a next step, EPA identified NPDES permit numbers for those permits not available inhouse. Some airports reported permit numbers in the airport questionnaire , so in these cases, EPA obtained the data from the questionnaire database. For the remaining airports, EPA searched its Envirofacts sear ch tool by facility name, location, SIC code (4581), or a combination of any of the three to obtain the permit numbers.

After identifying the permit numbers, EPA obt ained a copy of the permit from a state or regional permit database. If a permit was not av ailable online, EPA cont acted the appropriate regional, state, or local permitting authority to ob tain a copy. If still unsuc cessful in obtaining the permit, EPA contacted the airpor t directly to request a copy.

There were a few airports for which EPA c ould not identify permit numbers from either the questionnaires or Envirofacts. For these airp orts, EPA searched the Internet or contacted permitting authorities or the airports dire ctly to obtain a copy of the permit.

3 .5.3 Permit Review Process

The objectives of the permit review we re to answer the following questions:

• 

### What are the monitoring requireme nts for deicing area outfalls?

• 

### What pollutants are monitored?

• 

### Are there numeric limits listed in the permit for deicing area outfalls?

• 

### What parameters are limited?

• 

### What are the limits for each parameter?

• 

### How were the limits developed?

• 

### Are there deicing operation best manageme nt practices (BMPs) required by the permit?

• 

### What BMPs are required?

• 

### When does the permit expire?

• 

### If it is a general permit, are there di fferences between the permit and the EPA Multi-Sector General Permit (MSGP)?Technical Development Document for EffluentLimitation Guidelines and Standards for the Airport Deicing CategorySection 3 – Data Collection Activities

17Table 3-4. Top 50 Airports in the United States with theHighest ADF Usage, Estimated Based on SOFP Days and TotalAirport DeparturesRankAirportIDAirport CodeAirport NameStateSOFP DaysTotal AirportDeparturesWeighting FactorSOFP Days ×Departures ÷100,00011006ORDChicago O'Hare InternationalIL26467,721121.621126MSPMinneapolis /St Paul International – WoldChamberlainMN41246,286101.031138DTWDetroit Metropolitan Wayne CountyMI31250,62977.741028DENDenver InternationalCO26264,05168.751012ANCTed Stevens Anchorage InternationalAK5588,12648.561053BOSGeneral Edward Lawrence Logan International(Boston)MA26186,25348.471113CVGCincinnati/Northern Kentucky InternationalKY17247,16542.081069CLECleveland – Hopkins InternationalOH36116,56942.091142IADWashington Dulles InternationalDC17238,63540.6101107PITPittsburgh InternationalPA31125,14338.8111145EWRNewark Liberty InternationalNJ16203,08232.5121095MDWChicago Midway InternationalIL26108,38528.2131139PHLPhiladelphia InternationalPA12227,74927.3141136MKEGeneral Mitchell International (Milwaukee)WI3185,12826.4151029LGALa Guardia (New York City)NY12192,12723.1161066SLCSalt Lake City InternationalUT14160,47222.5171010FAIFairbanks InternationalAK8924,91922.2181011STLLambert - St Louis InternationalMO17129,41422.0191148MCIKansas City InternationalMO2776,01620.5201021BUFBuffalo Niagara InternationalNY4841,91620.1211089JFKJohn F Kennedy International (New York City)NY12154,60618.6221024INDIndianapolis InternationalIN2183,76917.6231141DCARonald Reagan Washington NationalDC12134,34616.1241129BDLBradley International (Windsor Locks)CT3151,38915.9251059ROCGreater Rochester InternationalNY4435,72615.7Technical Development Document for EffluentLimitation Guidelines and Standards for the Airport Deicing CategorySection 3 – Data Collection ActivitiesTable 3-4 (Continued)

18RankAirportIDAirport CodeAirport NameStateSOFP DaysTotal AirportDeparturesWeighting FactorSOFP Days ×Departures ÷100,000261111CMHPort Columbus InternationalOH2659,93815.6271036BWIBaltimore - Washington InternationalMD12124,03314.9281026DFWDallas/Fort Worth InternationalTX4360,93314.4291065ALBAlbany InternationalNY3639,32414.2301080SYRSyracuse Hancock InternationalNY4430,84013.6311140MEMMemphis InternationalTN8166,91013.4321128CLTCharlotte/Douglas InternationalNC6214,39612.9331079MHTManchesterNH3634,86012.5341058GRRGerald R Ford International (Grand Rapids)MI4825,01512.0351037IAHGeorge Bush Intercontinental (Houston)TX4248,3399.9361123DAYJames M Cox Dayton InternationalOH2635,7099.3371020ATLHartsfield - Jackson Atlanta InternationalGA2459,7659.2381121PVDTheodore Francis Green State (Providence)RI2143,6719.2391147RDURaleigh - Durham InternationalNC1086,3028.6401068OMAEppley Airfield (Omaha)NE2633,0228.6411105GEGSpokane InternationalWA3127,2698.5421108SDFLouisville International - Standiford FieldKY1265,5867.9431124DSMDes Moines InternationalIA3123,9517.4441074SBNSouth Bend RegionalIN4813,7226.6451153CAKAkron - Canton RegionalOH4114,9116.1461109ILNAirborne Airpark (Wilmington)OH2125,5085.4471018GSOPiedmont Triad International (Greensboro)NC1438,2575.4481100TOLToledo ExpressOH3614,3855.2491022FWAFort Wayne InternationalIN3116,2475.0501051HYABarnstable Municipal - Boardman/Polando Field(Hyannis)MA2618,7824.9Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

19 

### EPA also consulted Envirofacts as necessary to fill in any numeric limit data gaps from the permits and to cross-check for accuracy with the permitted limits.

To facilitate interpreting the re sults, EPA created a Microsoft ® 

### Access database to store the data obtained from the reviews. The database consists of two tables : a General Information table, and a Pollutant-Specific Information table. Table 3-5 and Table 3-6 detail the database table descriptions. A summary of the permit review is presented in the memorandum Airport Deicing Operations NPDES Permit Review Summary (ERG, 2007).

Table 3-5. Permit Review General Information Table

Data Element Data Element Description AirportID The airport identification number used for the Airport Questionnaire Permit_ID The airport NPDES identification number Permit_Expiration The permit expiration date Permit_BMPs A checkbox that identifies the presence of BMPs in the permit Permit_BMPs_Description A field that allows the BMPs in the permit to be listed General_Permit A checkbox that identifies general permits General_Permit_Difference from MSGP A field that describes any differences th at exist between general permits and the MSGP Permit_Monitoring A checkbox that indicates if the permit requires monitoring Permit_Limits A checkbox that indicates if the permit has numeric limits Permit_Limit_Rationale A field that describes what rationale was used to determine the limits in the permitTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

20 

### Table 3-6. Permit Review Polluta nt-Specific Information Table

Data Element Data Element Description AirportID The airport identification number used for the detailed airport questionnaire. Permit_SamPoint The outfall/sampling area identifying number. Permit_Stream_Description The description of the outfa ll/sampling area. EPA tried to determine which outfalls receive deicing stormwater and to includ e only information from those outfalls. If the deicing outfalls cannot be determined, EPA included all outfalls. Permit_Pollutant The pollutants that are monitored and/or limited at each outfall, using the following same codes that are used in the questionnaire database:

• BOD

• COD (chemical oxygen demand)

• Fecal coliform • Metal

• N (nitrogen)

• OG (oil & grease) • ORG (organic pollutants)

• pH

• TO C (total organic carbon) • TS S

• Other

OtherDesc If a pollutant is monitored/limited that does not have a code, “Other” was selected as the Permit_Pollutant and the pollutant name was entered in this field. This method of tracking pollutants was used to be consistent with the questionnaire database.
PermitTimes To be consistent with the questionnaire database, the frequency of monitoring for each pollutant and outf all was recorded in the PermitTimes and PermitFreq fields. These fields allow the frequency to be reported in a number/unit manner. For example, a yearly report is entered as PermitTimes = 1 and PermitFreq = Year. Frequency Codes were also used in the PermitFreq field for daily (D), monthly (M), and quarterly (Q) reports. PermitFreq

PermitLimitNumeric The numeric value of the permit limit for each pollutant and outfall.
PermitLimitUnit The unit of the permit limit for each pollutant and outfall. LimitType Indicates whether the limit is a mi nimum value, maximum value, average, or simply a reporting requirement. This also incorporates the time span of the limit using the frequency codes as above (e .g., daily maximum = DMAX; weekly average = WAVG).
Season For deicing outfalls, the limits may vary by season for various parameters. Usually, this field is populated with Summer, Winter, or All (as in year-round).



### 3 .6 Deicing Pad Costs

To evaluate the potential financial impact s of deicing pads for new airports, EPA reviewed deicing pad cost inform ation received from airports. EPA collected deicing pad costs from Pittsburgh International airport and Minneapo lis/St. Paul airport during the site visits, and information was provided by Akron-Canton Re gional airport via email on May 3, 2007, and from Cleveland-Hopkins International airport as part of comments in its airport questionnaire
response.

3 .7 Industry-Submitted Data

Based on airport site visits, EPA sampling episodes, and respons es to the airport questionnaire, EPA requested costing and long- term analytical data for managing deicing stormwater from specific airports. The Agency used this information to develop control technology options and compliance cost estimates, and to evaluate pollution prevention and best management practices.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

21 

### Table 3-7 and Table 3-8 list those airports pr oviding data, the type of system used to manage or treat the airport’s deicing stormwater, and the costing and/or analytical data submitted by the airport.

Table 3-7. Summary of Costing Data Provided by Industry

Airport Type of Deicing Stormwater Management Costing Data Provided Akron-Canton Regional Anaerobic ADF-contaminated stormwater treatment system Capital and operating and maintenance costs for the airport’s new anaerobic fluidized bed (AFB) treatment system Albany International AFB/aerobic ADF-contaminated stormwater treatment system Capital and operating and maintenance costs for the airport’s AFB/ae robic treatment system
Cincinnati/Northern Kentucky International Glycol recovery and recycling system Capital and operating and maintenance costs for glycol collection and treatment
Denver International Storage, recovery, and recycling; MVR and distillation system Capital costs for storage and the recycle/recovery system
General Mitchell International Recovery and recy cling; anaerobic digester Engineering and monito ring-related costs

Minneapolis/St. Paul International –Wold Chamberlain ADF collection (deicing pads, plug and pump system) Capital costs for deicing pads and operating and maintenance costs for plug and pump system Pittsburgh International ADF collection at deicing pads; ADF-contaminated stormwater recovery and recycling Operating and maintenance costs for deicing pads

Seattle-Tacoma International ADF to industrial waste treatment plant Study costs for determining all known and reasonable technology (AKART) for handling aircraft deicing fluids



### Table 3-8. Summary of Long-Term Anal ytical Data Provided by Industry

Airport Type of Deicing Stormwater Management Long-Term Analytical Data Provided Albany International Anaerobic/aerobic ADF-contaminated
stormwater treatment Ammonia, COD

Denver International Storage, recovery, and recycling; MVR/distillation COD

Detroit Metropolitan – Wayne County Recycling; distillation and recovery Ammonia

Pittsburgh International Ultrafiltration/Reverse Osmosis; ADFcontaminated stormwater recovery and recycling Ammonia, urea

Salt Lake City International ADF recovery and recycling CODTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

22 

### 3.8 Li terature Reviews

EPA conducted preliminary litera ture searches during the effluent guideline development process to supplement information acquired from site visits, sampling, and questionnaires. The purpose for the literature searches was three-fold:

• 

### To collect information on current airport deicing practices and trends, and gather information on state-of-the-art deicing stormwater treatment and/or glycol recovery technologies;

• 

### To collect available data from air ports currently monitoring wastewater discharges; and

• 

### To obtain studies on the toxicity and e nvironmental impact of current deicing fluids and deicing discharges.

The following sections list the data sources used for each literature search.

3 .8.1 Current Deicing Practices and Treatment Technologies

EPA performed keyword searches on thr ee online search engines: 1) Cambridge Scientific Abstracts (CSA); 2) Dialog Versi on 5.0; and 3) GoogleTM. CSA provides access to over 50 databases published by CSA and its pub lishing partners, such as Aqualine, Environmental Sciences & Pollution Management Database, and Water Resources Abstracts. Dialog provides access to over 900 databases and handles more than 700,000 searches. The databases in Dialog that contain articles pertaining to airpor t deicing are BIOSIS Toxicology, Life Sciences Abstracts, Inst itute for Science Information, Pr oQuest Info & Learning, Ei Compendex, Enviroline, TGG National Newspaper Index, GeoBase, National Technical Information Service (NTIS), and Wils on Applied Science & Technology Abs.

The keywords for the literature searches in cluded: airport deici ng, aircraft, airfield, runway, aircraft deicing, aircraft deicing fluid (ADF), runway de icing, anti-icing, anti-icing fluid, airport stormwater, snow me lt, centralized deicing pads, environmental assessment, environmental impact study (EIS), fish mortality, fish kill, and publicly owned treatment works.

EPA also used other online journal databa ses, such as Science Direct, Scirus, and Infotrak, for subject-specific articles. The treatment technologies featured in the articles found included:

• 

### AFB reactor/ biological treatment;

• 

### Aerated storage tanks;

• 

### Anaerobic co-digestion of ADF a nd municipal wastewater sludge;

• 

### Batch-loaded AFB reactor;

• 

### Glycol reclamation/recyc ling and concentration;

• 

### Infrared technology;

• 

### Phytoremediation;

• 

### Plan t-enhanced remediation;

• 

### Spra y irrigation;

• 

### Subsurface-flow constructed wetlands; and

• 

### Surface detention ponds.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

23 

### 3 .8.2 Current Airport Deicing Discharge Data

In addition to sampling and airport questionn aire data, EPA procur ed airport deicing discharge information from its Permit Complianc e System (PCS) database and online journals. EPA downloaded all data reports from PCS fo r SIC code 4581: Airpor ts, flying fields, and services. Not all airports report this data to th eir permitting authority, so the scope of discharge data is limited. The pollutant parameters incl ude temperature, dissolved oxygen, BOD, TSS, metals, fecal coliform, aromatic hydrocarbon, pH, and oil and grease. For online searches, EPA procured journals that disc ussed deicing discharge contai ning ADF chemicals such as benzotriazole, propylene/ethyle ne glycol, and alklyphenol et hoxylates. EPA also collected monitoring data during the site visit to the Minneapolis/St. Paul International Airport.

3 .8.3 Chemical Information and Environmental Impact Studies

The methodology and databases used for chemical information and environmental impact study findings are similar to those used for the deicing practices and treatment technology search. EPA conducted searches for the following categories:

• 

### Chem ical Properties of ADF Ingredients: Physical appearance, structure, solubility, reactivity;

• 

### Hu man Toxicity: Inhalation, ingestion, dermal eff ect, oral rat lethal dose (LD 50 

### ) values;

• 

### Aqua tic Toxicity: Aquatic life lethal concentration (LC 50 

### ) values; and

• 

### Chemical Fate and Transport: Soil sorption, fate in river, streams, and estuaries, breakdown pathways in anaerobic and aerobic conditions, and biodegradability.

In addition to journal articles, EPA gathered chemical information from Material Safety Data Sheets (MSDSs), Chemfinder.com, the Pesticides Action Network (PAN) Pesticides Database, and the U.S. Patents Database.

The keywords for the pollutant term search included: PG, PG-based fluids, EG, EG-based fluids, urea, potassium acetate, calcium magnesium acetate (CMA ), sodium acetate, sodium formate, dissolved oxygen, biodegradation, BOD, and ADF additives (e.g., tolytriazole, benzotriazole, nonylphenols, nonylph enol ethoxylate, etc.).

3 .8.4 Current Deicing Discharge Regulations

In addition to the data sources describe d above, EPA searched the Internet using GoogleTM to review regulatory documents th at contain guidelines , operation controls, management programs, laws, statutes, and certific ation requirements relate d to airport deicing from the United States, Canada, Germany, Norway, and other European countries.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

24 

### 3 .9 Data Collected Based on Public Comments

EPA collected and received limited additional in formation as part of the public comment process. This section summarizes the information EPA collected as part of and in response to public comments on the proposed rule and the type s of data provided as part of the public comments. Section 3.9.1 summarizes information th at EPA collected to confirm deicing pad use and operations at major airports a nd data collected to supplement th e costing effort in response to comment. Section 3.9.2 summarizes the types of data submitted as part of the public comments to the proposed rule.

3 .9.1 EPA-Collected Data

EPA received comments on the proposed regulati on that airports that had previously installed deicing pads did not use them for all f lights that required deic ing. EPA contacted the following airports in early Augus t 2010 to confirm information on the airport’s deicing pad use and operations:

• 

### Minneapolis/St. Paul International Airport (MSP);

• 

### Washington Dulles Intern ational Airport (IAD);

• 

### Philadelphia Internati onal Airport (PHL);

• 

### Detroit Metropolitan/Wayne County Airport (DTW);

• 

### Denv er International Airport (DEN);

• 

### Cle veland-Hopkins International Airport (CLE);

• 

### S alt Lake City International Airport (SLC); and

• 

### Pi ttsburgh International Airport (PIT).

Table 3-9 summarizes the information collected for these airports.

EPA also collected additional post-proposal inform ation as part of revisions to the costing analysis in response to specific public commen ts. Additional costing in formation collected by EPA included drainage cover data that it used in conjunction with existing cost data for Glycol Collection Vehicles (GCVs). The supplemental data collected to inform GCV costing is summarized in a memorandum entitled Estimated Capital and Oper ation and Maintenance Costs for Glycol Collection Vehicle Operation (ERG, 2010a). EPA also collected vendor data related to liquid application and storage of airfield deicing chemicals. Th ese data are summarized in the memorandum entitled Estimated Costs for Transition to Liquid Airfield Deicing Application from Solid Airfield Deicing (ERG, 2010b). In addition, Section 10 presents the liquid application and storage of airfield deicing chem ical cost data used in developi ng the final rule cost analysis.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

25 

### Table 3-9. Selected Airport Informatio n Related to Deicing Pad Operations

Airport Deicing Pad Operations Data Minneapolis/St. Paul International Airport 1. MSP encourages the use of deicing pads and requires deicing in contained locations only. ADF stormwater is contained through deicing pad use (and its collection system), block and pump, and cover and sweep (using glycol collection vehicles). There are no exceptions to th e requirement for contained locations for deicing operations.

2. MSP estimates that 65-70% of ADF fluid used at the airport is sprayed at its deicing pads. The percentage of flights represented by this amount of ADF fluid use is much lower than 65-70%. The deicing pads are typically used for heavy deicing and not for defrost deicing. Delta, previously Northwest Airlines, deices at both the gate and at the deicing pads. Overall, they spray more deicing fluid at the pads than at the gates. This airline does not generally act as an FBO for other airlines but may be used as a deicing provider in a backup situation. The small airlines operating at the airport do not have personnel for deicing pad use.

3. If deicing is not done on the deicing pads, it is done at the gate.

4. Advantages of the MSP deicing pads include putting the deiced aircraft closer to the runway, which lowers the chance of missing ADF holdover times, and freeing up the gates for incoming flights. Washington Dulles International Airport 1. Approximately 50% of the flights deiced at IAD are deiced on deicing pads. In addition, the airport requires that flights be deiced in areas of capture that may include glycol collection vehicles.

2. There are no specific requirements on where each airline has to deice their planes. The location of where each airline plans to deice is decided between the airlines at winter "snow meetings." Philadelphia International Airport 1. All commercial aircraft except commuter aircraft (regional jets and turbo-props) must be deiced at the airport deicing pa d, as specified in the airport’s NPDES permit.

2. Aircraft defrosting is permitted at the gates with a usage limit of 20-40 gallons of ADF, as specified in th e airport’s NPDES permit.

3. Deicing of the plane is also permitted at the gate with no ADF usage limit, for required weight reduction or visibility enhancement, sufficient to safely taxi the aircraft to the deicing pad for final, pre-take-off ADF application. Detroit Metropolitan/Wayne County Airport 1. DTW does not have a specific requirement forcing the airlines to deice aircraft at the deicing pads but does strongly encourage deicing pad use.

2. The airport estimates that approximately 90% of the airport traffic that is deiced uses the deicing pads.

3. The airport allows 747s to deice at the gates to free up the deicing pads for smaller aircraft. Airport study of this allowance shows that it achieves a higher net capture of ADF using this approach. The airport collects ADF stormwater from the 747 deicing using a glycol collection vehicle in conjunction with catch basin inserts.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities



### Table 3-9 (Continued)

26 Airport Deicing Pad Operations Data Denver International Airport 1. DEN does not allow full-plane gate deicing, and does not track limited gate deicing operations specifically (other than to enforce the 25-gallon rule discussed in item 3. below). The airport tracks only the volume of fluid used on an airport-wide basis but estimates that 95% of deicing occurs on the dedicated deicing pads. DEN's largest carrier, United Airlin es (UAL), does provide DE N (Environmental Services) with its fluid usage data, including by location. UAL's data show approximately 6% of its total fluid used was applied at the gates pursuant to DEN's 25-gallon operational allowance. UAL's data do not pr ovide the number of flights deiced by location. On average, UAL accounts for approximately 27% of the total aircraft deicing fluid applied at DEN.

2. DEN is not aware of any specific inst ances of deicing outside the designated areas (pads, gates (limited), GA, South Cargo). If it did occur, it would be a very rare occurrence under special circumstances, and would require prior approval from the Manager of Aviation.

3. Limited deicing requirements are stipulated on page 6 of DEN Rule and Regulation Part 190 - Aircraft Deicing Regulations. The language does not specify for what purpose limited deicing may occur, only that "In no event may the total amount of deicing fluid used in a limited deicing exceed 25 gallons neat (undiluted) ADF per aircraft.” DEN R&R Part 190 can be accessed directly at http://business.flydenver.com/info/research/rules/index.htm.

4. On a volume-only basis, for the 2008/2009 season, DEN data show approximately 5% of the total amount of deicing fluid used at DEN was applied at South Cargo and General Aviation (combined). Cleveland-Hopkins International Airport 1. CLE estimates that 90% of deiced flights are deiced at deicing pads and the remaining 10% are deiced at the gate. Most of the air carriers are not allowed to deice at the concourse gates.

2. For those air carriers not allowed to deice at the gate, the airport does allow emergency deicing to unfreeze the wheels or other plane parts to allow the plane to move safely to the deicing pad. Salt Lake City International Airport 1. At SLC, 95-98% of the deiced flights are deiced on pads and each major airline has its own dedicated deicing pad.

2. All deicing is to occur on the deicing pads except for specific circumstances that are typically delay related. Pittsburgh International Airport 1. Aircraft deicing at the airport is requ ired by consent decree to occur on deicing pads. Thus, 100% of deiced flights are deiced on the airport's pads unless doing so will result in a total loss of operations (e.g., major delays or if the deicing pad is out of ADF). The airport does allow gate deicing for both defrost and safety purposes.

2. PIT defines defrost deicing as "the removal of contamination (frost) from critical components of the airport that occurs when there is no active precipitation" and defines regular deicing as “the removal of contamination (snow/ice) that occurs when there is or has been active precipitation."

3. When an air carrier conducts gate deicing (instead of using the deicing pads), it must document why the deicing occurred at the gate.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 3 – Data Collection Activities

27 

### 3.9.2 Da ta Submitted with Public Comments

All comments received on the proposed airp ort deicing rulemaking are available in the docket. In assessing comments, EPA evaluated, and in some cases used, data or suggestions provided by specific commenters for the final rule analyses. While the data submitted by commenters were useful, in genera l, commenters provided very little analytical data on treatment or collection performance. Commenters, however , did provide some new data related to the costing analysis and on the feasib ility of deicing pads . Section 10 summarizes the data used to develop EPA’s final rule costs. As an example, EPA incorporated industr y-supplied data on AFB capital costs versus COD loading in its final costing analysis (see Figure 10-1 ).

Comments by specific airports/port authori ties on the proposed rule, including BostonLogan International Airport and The Port of New York and New Jersey, included docum entation supporting a claim that their airports are space-constrained and they would not be able to locate a deicing pad facility to comply w ith the proposed rule. EPA consider ed this data in developing the final rule and is no longer requiring collection of spent ADF at existing airports.

3.10 Ref erences
ERG. 2007. Memorandum from Jason Huckaby (ERG ) to Brian D’Amico and Eric Strassler (U.S. EPA). Airport Deicing Operations NPDES Permit Review Summary . (April 16). DCN AD00611.

ERG. 2010a. Memorandum from Steve Strackbe in and Mary Willett (ERG) to the Airport Deicing Administrative Record. Estimated Capital and Operation and Maintenance Costs for Glycol Collection Vehicle Operation . (October 8). DCN AD01249.

ERG. 2010b. Memorandum from Steve Strackbein and Mary Willett (ERG) to Brian D’Amico and Eric Strassler (U.S. EPA). Estimated Costs for Transition to Liquid Airfield Deicing Application from Solid Airfield Deicing . (October 8). DCN AD01252.

USEPA. 2000. Preliminary Data Summary: Airport Deicing Operations. U.S. Environmental Protection Agency. Washington, D.C. EPA-821-R-00-016. Available online at http://www.epa.gov/guide/airport . DCN AD00005.

USEPA. 2005. Supporting Statement: Survey of Airport Deicing Operations. U.S. Environmental Protection Agency. Washington, D.C. DCN AD00447.

USEPA.2008a. Airline Screener Questionnaire Database. U.S. Environmental Protection Agency. Washington, D.C. DCN AD00937.

USEPA. 2008b. Airline Detailed Ques tionnaire Database. U.S. Environmental Protection Agency. Washington, D.C. DCN AD00938.

USEPA. 2008c. Airport Questionnaire Database. U.S. Environmental Protection Agency. Washington, D.C. DCN AD00927.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry

28 

### 4. O VERV IEW OF THE 

### I NDUSTRY


### This section provides an overview of the air port deicing/anti-icing performed by selected airports and airlines. The overview includes statis tics on the number and lo cation of airports and airlines that perform deici ng/anti-icing (Section 4.1) and de icing and anti-icing practices performed on airfields a nd aircraft and methods used to colle ct and control deicing stormwater (Section 4.2).

4.1 In dustry Statistics

Data sources for statistics on the number a nd types of airports and airlines include responses to EPA’s airport and ai rline questionnaires, the Bureau of Transporta tion Statistics, FAA, and EPA’s Preliminary Data Summary: Airport Deicing Operations (PDS) (USEPA, 2000). Data provided in respons es to EPA questionnaires ar e based on deicing/anti-icing operations performed during the wint er seasons of 2002/2003, 2003/2004, and 2004/2005, hereafter referred to as the three winter seasons.

4.1.1 Ai rports
The North American Industry Classification System (NAICS) identification number applicable to airport deicing is 488119: Other Airport Operations. The U.S. Census Bureau describes this industry as establishments pr imarily engaged in the following: (1) operating international, national, or ci vil airports or public flying fi elds, or (2) supporting airport operations, such as runway maintenance services , hangar rental, and/or cargo handling services.

The airport questionnaire data presented in this section are base d on the 150 respondents to EPA’s airport questionnaire. EPA applied we ighting factors to the information provided by selected airport questionnaire re cipients to scale up the questionna ire data to represent national estimates.

4.1.1.1 Number and Types of Airports

FAA’s general categories of ai rports include commercial, gene ral aviation, and relievers. Commercial airports are public airports receiving schedul ed passenger service and having more than 2,500 enplaned passengers (number of passenge rs boarding a plane for departure) each year. General aviation airports have less than 2,500 enplanemen ts per year or do not receive scheduled commercial service. Relievers are high-capacity general aviati on airports in major metropolitan areas, and provide an alternative for sma ll aircraft using busy commercial airports.

Airports may be further classified into several different categories, depending on the size and activity level of the airport. Often both of these f actors can be determined by the number of enplanements or operations (number of arrivals and departures) at the ai rport in a given year. FAA classifies large commercial airports into “hubs,” based on the number of annual enplanements that occur at the airport. Large H ubs are defined as airports with more than 1 percent of total U.S. passenger enplanements. Me dium Hubs are defined as airports with more than 0.25 percent but less than 1 percent of total passenger enplanements. Small Hubs account for 0.05 to 0.25 percent of the tota l passenger enplanements. Airports with less than 0.05 percent of the total passenger enplanements but more than 10,000 annual enplanements are consideredTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry

29 

### Non-hub primary airports. Nonprimary commercial se rvices are those airpor ts that have 2,500 to 10,000 enplanements a year.

According to FAA 2004 data and the FAA’s Na tional Plan of Integrated Airport Systems (NPIAS) Report to Congress, a bout 3,344 airports operated in the United States in 2004. Table 4-1 identifies the number of air ports by type as defined by number of enplanements. For all airport types, excluding general aviation airports, the totals in Table 4-1 represent counts for January through December 2004. FAA’s designation of hub status depends on the percentage of total passenger boardings occurring at each airp ort, causing the number of airports in each hub category to vary from year to year.

Table 4-1. Number of U.S. Airports by Airport Type in 2004

Airport Type Number of Airports Large Hub 33
Medium Hub 36
Small Hub 67
Non-hub 231 Other Nonprimary 130
General Aviation 1 2,573
General Aviation Relievers 1 274
TOTAL 3,344

1 General aviation and general aviation reliever airports (o pen to the public) from th e NPIAS Report to Congress (USDOT, 2008a). Note: Airport counts will differ depending on the source and year of data represented.



### EPA distributed the airport questionnaire to 153 airports that included, based on 2004 information, all Large Hub, all Medium Hub, and a statistical sampling of Small Hub and Nonhub airports, as well as judgment sampling of some general av iation/cargo, and other nonprimary airports. EPA determined that one airport reci pient was out of scope and removed it from the sample frame. EPA received responses from 150 of these airports. Using the airport responses and their statistical weights and including the cargo airports and Alas kan airport judgment samples, EPA estimated that the number of primar y commercial airports nationally that perform deicing and/or anti-icing of airfield pavement and/or aircraft is 334.

4.1 .1.2 Geographic Location of Deicing Airports

The location of the airport and its climate have a direct impact on deicing operations. Airport deicing/anti-icing operations occurred in 44 states in the three winter seasons. As shown below, the FAA divides the United Stat es into the following nine regions:Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry

30 Region State
Alaskan AK
Central IA, KS, MO
Eastern DE, MD, NJ, NY, PA, VA, WV
Great Lakes IL, IN, MI, MN, ND, OH, SD, WI New England CT, ME, MA, NH, RI, VT
Northwest Mountain CO, ID, MT, OR, UT, WA, WY
Southern AL, FL, GA, KY, MS, NC, PR, TN, VI
Southwest AR, LA, NM, OK, TX
Western-Pacific AZ, CA, HI, NV, GU, AS, MH Source: FAA, “FAA Regional Offices,” http://www.faa.gov/about/office_org/headquarters_offices/arp/ regional_offices/ (U.S. DOT, 2008b).



### Table 4-2 summarizes the regions for the airports that reported deicing in the EPA airport questionnaire for the three winter seasons surveyed by EPA. (Note: these are not national estimates.) The Great Lakes and Eastern regions reporte d the highest number of deicing airports.

Table 4-2. Deicing Airports by FAA Region for the Three Winter Seasons

Region Airports Reporting Deicing and/or Anti-Icing in EPA Airport Questionnaire
Great Lakes 31
Eastern 22
Southern 20
Northwest Mountain 17
Western-Pacific 15
Southwest 14
Alaskan 10 New England 6
Central 5 Source: EPA airport questionnaire database (USEPA, 2008c).



### 4.1.1 .3 Weather Impacts on Airp ort Deicing/Anti-Icing

Airports conduct deicing/an ti-icing operations when w eather conditions, such as precipitation and/or temperature, have the potential to cause icing. Precipitation includes snowfall, rainfall, sleet (including freezing rain), and ice. The type of pr ecipitation affects the volume and type of deicing/anti-icing chemical s used on aircraft and airfield pavement. For example, freezing rain requires the most deicing/ anti-icing agent usage because the rain freezes on contact and coats the ai rcraft or airfield pavement to form a solid layer of ice. Dry-weather deicing, performed when the ambient temperature is cold enough to form ice on aircraft wings and surfaces (below 55° F), generally requires only a small volume of ADF.

The duration of the deicing/an ti-icing season is also determined by the climate at an airport location. Airfield pavement deicing can begin as early as September and continue through May in colder climates and/or areas with hi gh numbers of snow or freezing precipitation days.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry 

### The national estimate of airports performing airfield pavement deic ing is 215; this is lower than the national estimate of airports performing deicin g operations overall because there are airports that have some aircraft deicing (usually defros t deicing) but no airfield pavement deicing. In general, these airports are loca ted in warm and/or dry weather climates with minimal winter storm events. For months when airfield pave ment deicing occurs, December, January, and February have the most occurren ces of airfield pavement deic ing, and September and May have the lowest. Figure 4-1 presents the percentage of these 215 ai rports deicing airf ield pavement for each month. The time frame during which an air port conducts deicing during a typical winter season ranges from two to nine months, and a majo rity of airports typically conduct deicing/antiicing operations for five months a season. For th e three winter seasons surveyed by EPA, the average reported number of airfield pavement deicing days among these 215 airports ranges from 0.3 to 240 days.

71% 69%

61%

27%

5%

0% 0% 0% 5% 24% 55% 71%

0% 10% 20% 30% 40% 50% 60% 70% 80%

J anuary

F e br

u ar

y M ar ch April May June July Au gu

s t Sept em

ber October

N ovem b er December

MonthPercentage



### Figure 4-1. Percentage of Airports Deic ing Airfield Pavement Each Month

4.1.1.4 Destination of Airport Deicing Stormwater

Airport questionnaire respondents reported direct, indirect, an d zero discharge of deicing stormwater. Direct dischargers discharge deicin g stormwater directly to U.S. surface waters, such as creeks, rivers, ponds, lakes, or oceans. Indirect dischargers conv ey deicing stormwater by pipe, conduit, or hauling to a publicly owned or other treatme nt works. A zero discharger disposes of deicing stormwater using methods other than dir ect or indirect discharge. Figure 4-2 presents the reported discharge stat us of airports by destination. S caling the questionnaire data to a national estimate results in 176 airports disc harging to surface water only, 52 airports

31Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry 

### discharging both directly to surf ace water and indirectly to a POTW , 10 airports discharging to a POTW only, and 96 airports reporting zero discharge.

Direct Discharge Only 52%

Direct and

Indirect Discharge 16% Indirect Discharge Only 3% Zero Discharge 29%



### Figure 4-2. Discharge Status of Airports

A majority of the zero dischargers reported conducting aircraft deicing only (i.e., no deicing of airfield pavement). Th ese airports generally are in wa rm and/or dry weather climates and have minimal dry weather (defrost) deici ng. Airports reported various methods for maintaining zero discharge that included evapor ation, storage in surface impoundments, contract hauling, and recycle/recovery of deicing stor mwater. The most common zero discharge method reported was evaporation followed by discharg e to a surface impoundment and the “other” category. The methods identified as “other” zer o discharge techniques included, infiltration, discharge to tundra over permafrost , use of drain covers and sorben t material, and use of BMPs.

Even though over 100 airports indicated that they do not have any direct discharge (96 zero discharge and 10 POTW only) of ADF-c ontaminated stormwater, EPA believes that fugitive ADF emissions from overspray and trac king and dripping, during taxiing and takeoff, are difficult if not impossible to track and will likely result in direct discharges, albeit potentially small ones.

4.1.2 Ai rlines

The NAICS code for airlines is 481: Air Transportation. Specific NAICS codes for respondents to the airline deicing questionnair es are: (1) 481111: Scheduled Passenger Air Transportation, described by the U. S. Census Bu reau as establishments primarily engaged in providing air transportation of pa ssengers or passengers and frei ght over regular routes and on regular schedules; and (2) 481112: Sc heduled Freight Air Transportation, described by the U.S. Census Bureau as establishments primarily e ngaged in providing air transportation of cargo without transporting passengers over regul ar routes and on regular schedules.

32Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry

33 

### The airline data presented in this section are based on the 49 respondents to EPA’s airline detailed questionnaire and addi tional information from the 70 respondents to EPA’s airline screener questionnaire. Statistics for airlines do not have weigh ting factors and are based on the actual number of respondents.

4.1.2 .1 Types of Airlines

The four classifications of ai rlines are major, national, re gional, and cargo and are based on the type of service they o ffer and their annual revenues. Classification is based on the economic and financial aspects of each airline’s aircraft fleet. Table 4-3 lists the criteria for the four classifications.

Table 4-3. Airline Classifications

Airline Type Annual Revenues Type of Service Aircraft Fleet Major >$100 million Regular schedules Large jets: >60 seats Payload >18,000 lbs
National $100 million to $1 billion Regular schedules Medium and large jets Regional: Limited to single U.S. region Large $20 million to $100 million Scheduled >60 seats
Medium <$20 million Scheduled Lesser or greater than 60 seats
Small (commuters) No revenue cut-off Scheduled <30 seats

Cargo No revenue cut-off Scheduled Passenger aircraft with seats removed
Source: Preliminary Data Summary: Airport Deicing Operations (Revised) (USEPA, 2000).



### There were 20 major airlines in the Un ited States in 2006. Many national airlines typically serve multiple U.S. regions whereas regional airlines are generally limited to a single region of the country.

Small regional airlines are the largest segmen t of the regional airline business. Regional airlines may be private business carriers, commer cial airlines, charter airlines, or provide a combination of these services. Private business carriers represent about 60 percent of regional airline flights. Regional airlines serve all airpor ts served by major airlines as well as smaller airports that are not served by any major airline. They typicall y operate out of one gate area unless they are affiliates of major airlines and operate at the gates of their affiliate. Regional airlines conduct a disproportiona tely large number of flight ope rations per passenger because their aircraft are smaller and carry fewer passengers per operation.

All respondents to the airlin e detailed questionnaire re ported conducting deicing/antiicing operations on their aircraft at a total of 57 ai rport locations.

4 .1.2.2 Types of Airline/Airport Relationships

The relationship between airpor ts and airlines regarding de icing operations is one of dependency and cooperation. Airp orts and airlines conduct deicing using chemical and nonchemical methods in the same airfield locatio ns and both contribute pollutants to deicing stormwater. Airlines may conduct deicing on their own aircraft, deicing for other airlines, and/orTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry

34 

### may also use FBOs. An airline’s deicing methods must be approved by the FAA for air safety. Airports provide the collection a nd control systems to contain a nd/or treat deicing stormwater generated as a result of aircraft and airfield deicing. However, both airports and airlines implement pollution prevention practices such as evaluating application ra tes, using alternate chemicals, pretreating pavement and aircraft, and manually removing snow and ice to reduce the quantity of pollutants discharged and the amount of deicing stormwater generated.

4 .2 Industry Practices

Airport deicing and anti-icing operations invol ve chemical and mechanical methods and are conducted at varied locations and by different entities. This section di scusses these practices and pollution prevention methods us ed by airports and airlines as reported by respondents to the airport and airline de icing questionnaires.

4

.2.1 Airfield Deicing Practices

Airfield pavement deicing/anti-icing rem oves or prevents the accumulation of frost, snow, or ice on runways, taxiways, aprons, ga tes, and ramps. These methods are typically conducted by airport personnel, FBOs, or private contractors using a comb ination of mechanical methods and chemical deicing/anti-icing agents . To reduce the quantity of pollutants or the amount of deicing stormwater gene rated, airports also use various pollution prevention measures.

Responses to EPA’s airport que stionnaire indicated that 67 percent of airports have the primary responsibility for airfield pavement deicing/anti-icing.

4 .2.1.1 Chemical Deicing/Anti-Icing

The type of precipitation and temperature aff ect the volume and type of deicing agents required for deicing/anti-icing. Co mmon pavement deicing/anti-ici ng agents used at airports include potassium acetate, sand, airside urea, sodi um acetate, glycol-based fluids, and sodium formate, as reported by respondents to EPA’s ai rport questionnaire. Potassium acetate and PGbased fluids were reported as th e top deicing/anti-icing chemicals (by weight) used on airfield pavement during the three winter seasons surv eyed by EPA; some respondents also reported using a mixture of these agen ts as well as heated sand. Table 4-4 provides national estimates of the number of airports using these agents. Airpor ts purchase primarily ready-to-apply rather than concentrated formulations of these chemicals. See Section 6.1 for a detailed discussion of deicing chemical usage.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry

35 

### Table 4-4. National Estimate of Airports Using Deicing Chemicals or Materials

Deicing/Anti-Icing Chemical or

Material Number of Airports Using Deicing Chemical/Material

Average Percentage of Airports Using Deicing Chemical/ Material 2002/2003 2003/2004 2004/2005
Potassium Acetate 94 104 111 103 31
Sand 103 104 98 102 30
Airside Urea 58 60 59 59 17
Sodium Acetate 39 34 33 35 10
PG-Based Fluids 16 16 16 16 5
Sodium Formate 22 1 23 15 5
EG-Based Fluids 6 6 6 6 2 Source: EPA airport questionnaire responses (scaled to national estimates) (USEPA, 2008c).



### 4 .2.1.2 Mechanical and Nonchemical Deicing/Anti-Icing

Mechanical methods, such as plows, brushes, blowers, and shovels for snow removal, are the primary forms of airfield pavement deicing and may be used in combination with chemical methods. One facility uses heated pavement th rough pavement temperature sensors to prevent airfield pavement from icing. All of the 215 airports that conduct pavement deicing use some form of chemical, while an estimated 212 (99 percent) use mechanical methods as well on airfield pavement.

4

.2.2 Aircraft Deicing Practices

Aircraft deicing involves removing frost, snow , or ice from aircraft. Aircraft anti-icing entails preventing frost, snow, or ice from accumu lating on aircraft surfaces. Both chemical and nonchemical deicing/anti-icing methods are conducted on aircraft at varied airport locations and by different entities. The FAA also influences airc raft deicing, as it has a pproval authority for the deicing/anti-icing practices and procedures sele cted. Airlines and FBOs also perform pollution prevention practices similar to ai rports to reduce the quantity of pollutants discharged and/or reduce the amount of deici ng stormwater generated.

Aircraft deicing may be conducted by an airlin e, FBO, or private contractor. Often, larger airline carriers deice thei r own aircraft and possibly the aircraft of other airlines . In addition, the entity conducting aircraft deicing for an air line may vary depending on the airport location. All of the airline questionnaire respond ents reported deicing their own ai rcraft at one or more of their airport locations. Airline responde nts also reported FBOs and/or another airlin e deiced their aircraft (84 percent and 56 per cent, respectively) at some of their airport locations.

Aircraft deicing is conducted at a variety of airport locations a nd may be conducted at multiple types of locations at the same airport. Aircraft deicing is most commonly performed at deicing pads and terminal gates and apron areas. Airline respondents reported aircraft deicing at the following locations (the percentage of the airline respondents repo rting using the specific type of location is in pararentheses):Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry

36 

### • 

### Deicing pad (80 percent);

• 

### Passen ger terminal gates/apron areas (78 percent);

• 

### Aircraft parking aprons (46 percent);

• 

### Airfield ramps (42 percent);

• 

### Taxiways (24 percent);

• 

### Cargo a pron areas (16 percent); and

• 

### Othe r locations (12 percent) (e.g., hangar).

4 .2.2.1 Chemical Deicing/Anti-Icing

The type of precipitation and temperature in fluences the volume and type of deicing chemicals required to deice/anti- ice aircraft. Two types of airc raft deicing are conducted: wetweather and dry-weather. Wet-w eather deicing is conducted when snow, sleet, or freezing rain accumulates on the aircraft. Dry-weather deicing is conducted when frost or ice forms on the aircraft due to changes in the ambient temperat ure or when fuel tanks become cooled during high-altitude flight, forming ice at lower altitudes and af ter landing. Dry-weather deicing requires significantly smaller volumes of ADFs than wet-weather deicing.

Aircraft deicing/anti-icing chemicals are categor ized into four classes: Type I, Type II, Type III, and Type IV. Not all types are curre ntly used. Airlines surveyed by EPA reported consistently using only Type I and Type IV fluids. ADFs vary by composition and allowable holdover times (i.e., the amount of time the residual fluid protects aircraft from ice formation). They generally contain either EG or PG, water, and additives to remove or prevent ice and snow. Type I ADF is used to remove ice and snow that has accumulated on aircraft, and Type IV fluids are used for anti-icing to increase holdover times for an aircraft pr ior to takeoff. Deicing fluids are usually heated prior to application, while an ti-icing fluids are typica lly applied at ambient temperatures.
All fluids are usually applied under pressure using a nozzle, often from mobile deicing trucks (as reported by 31 airlines). Below are additional types of ADF application equipment used, as reported in responses to the airlin e questionnaire:

• 

### Other equipment (e.g., brooms, ground spra yer and ladder, palletized equipment and fork lift, towed tower, small porta ble unit, self-contai ned mobile unit);

• 

### Fixed booms; and

• 

### Handheld bottle/containers.

Table 4-5 identifies the types of ADF fluids purch ased by airlines that deiced their own aircraft during the three winter seasons, as we ll as the average across those seasons, based on the 49 airline respondents to the ai rline detailed questionnaire. Table 4-6 lists the ADF fluids purchased by an FBO during the three winter se asons and the average across those seasons, as reported in the airline questionnaire . As shown in the tables, Type I and Type IV PG are the most commonly purchased ADF fluids for deicing aircraft, both by airlines that deice their own aircraft and airlines that use FBOs.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry

37 

### Table 4-5. Deicing/Anti-Icing Chemicals Purc hased by Airlines that Deiced Their Own Aircraft

Deicing/Anti-Icing Chemical Number of Airlines Purchasing Chemicals Average Number of Airlines Purchasing Chemicals 2002/2003 2003/2004 2004/2005 Type I PG 29 29 28 29 Type IV PG 22 22 23 22 Type I EG 8 8 8 8 Type IV EG 6 5 4 5 Type II PG 0 0 1 1 Source: EPA airline detailed questio nnaire database (USEPA, 2008b).



### Table 4-6. Deicing/Anti-Icing Chemicals Purchased for Aircraft Deiced by an FBO

Deicing/Anti-Icing Chemical Number of Airlines for Chemicals Purchased by an FBO Average Number of Airlines for Chemicals Purchased by an FBO 2002/2003 2003/2004 2004/2005 Type I PG 35 36 39 37 Type IV PG 31 35 37 34 Type I EG 17 13 13 14 Type IV EG 13 9 9 10 Type II PG 0 2 1 1 Type II EG 0 0 1 1 Source: EPA airline detailed questio nnaire database (USEPA, 2008b).



### 4 .2.2.2 Mechanical and Nonchemical Deicing/Anti-Icing

Mechanical and other nonchemical methods used to deice aircraft include brooms, ropes, hot water, infrared heating, and forced air. Brooms and ropes are not the primary method of aircraft deicing, especially wet-weather deicing, because they are so time- and labor-intensive, but rather are used in combination with chemical deicing. Forced air/hot air systems are used to blow or melt snow and ice from aircraft surfaces. Infrared heating deicing systems consist of an open hangar-type structure with infrared generators suspended from the ceiling. The infrared wavelengths are targeted to heat ice and snow and minimize heating of aircraft components. This system reduces the volume of ADF fluid required, but cannot provide anti-icing protection. Aircraft may also be stored in a hangar to pr event snow or ice from accumulating if a storm event is predicted. The most common mechanical and nonchemical methods of deicing/anti-icing used by airline questionnaire respondents ar e mechanical methods and hangar storage. Table 4-7 and Table 4-8 summarize the use of these methods for de icing/anti-icing aircraft by airlines and by FBOs, respectively.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry

38 

### Table 4-7. Summary of Mechanical and Nonchemi cal Aircraft Deicing Methods Used by an Airline

Mechanical/Nonchemical Method Number of Airlines Average Number of Airlines 2003/2004 2003/2004 2004/2005 Mechanical (e.g., brooms, ropes) 22 21 21 21 Hangar storage 15 16 16 16
Forced air 9 7 7 8
Hot water 5 4 4 4 Infrared heating 1 1 1 1 Source: EPA airline detailed questio nnaire database (USEPA, 2008b).



### Table 4-8. Summary of Mechanical and Nonche mical Aircraft Deicing Methods Used By FBOs

Mechanical/Nonchemical Method Number of Airlines Average Number of Airlines 2003/2004 2003/2004 2004/2005 Mechanical (e.g., brooms, ropes) 10 10 10 10 Hangar storage 5 5 5 5
Forced air 4 5 5 5
Hot water 3 4 4 4 Infrared heating 0 0 0 0 Source: EPA airline detailed questio nnaire database (USEPA, 2008b).



### 4

.2.3 Airport Deicing Stormwater Collection and Control

Deicing and anti-icing operati ons are conducted at multiple lo cations at an airport, and the fluids are widely dispersed during and af ter application via ramp discharge, taxiway drippage, and residual on airc raft. Deicing stormwater is contained and collected using designated deicing areas, stor mwater drainage systems, gl ycol recovery, storage tanks, containment ponds, and plug and pump systems. T ypical sources of deicing stormwater are:

• 

### Terminal gates and aprons/areas;

• 

### Aircraft deicing pads;

• 

### Taxiways;

• 

### Airfield ramps;

• 

### Runw ays;

• 

### Ca rgo apron areas;

• 

### M aintenance hangar ramps;

• 

### Ai rcraft parking areas;

• 

### Mili tary bases; and

• 

### ADF- contaminated snow dumps.

Table 4-9 summarizes the collection and contro l methods used by airports. Based on responses to the airport ques tionnaire, an estimated 246 U.S. airports use containment, collection, and/or conveyance measures to cont rol the discharge of deicing stormwaters to surface waters and/or POTWs. Most of the airports use stormwater drainage systems andTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry

39 

### containment ponds and basins. See Section 9.0 for detailed discussions of deicing stormwater collection and control methods used by the Airport Deicing Category.

Table 4-9. Summary of Airport Collection, Containment, and Conveyance Methods

Collection/Containmen t/Conveyance Method Estimated Number of Airports Percentage of Airports Stormwater drainage system 211 63 Containment pond/basin 121 36 Aboveground/underground tank 57 17 Glycol collection vehicles/sweepers 54 16 Other (vegetated swales, snow melters, absorbant) 34 10 Plug and pump 29 9 Source: EPA airport questionnaire database (scaled to national estimate) (USEPA, 2008c).



### EPA estimates that approximately half (46 pe rcent) of the U.S. airports with deicing operations also operate systems to treat or rec over their deicing stormwater. The treatment and recovery technologies reported by airports include equa lization (46 percent), oil/water separation (5 percent), sand or other media filtration (4 percent), membrane separation (1 percent), and biological treatment (1 percent) . Eight percent of the airports report using other types of treatment technologies, including MVR, aeration, and distillation. Section 7 describes these technologies in detail.

4.2 .4 Pollution Prevention Practices

To reduce the quantity of pollutants discharg ed and the amount of deicing stormwater generated, airports implement various pollution pr evention practices that control pollution from airport deicing chemicals (e.g., glycol), thus mi nimizing pollutant loads by reducing chemical usage. Physical snow removal, specialized employee training, and pretreatment of airfields in advance of precipitation are the most common practices used by ai rports for airfield pollution prevention. The national estimate of airports implementing one or more pollution prevention practices is 244. Table 4-10 summarizes EPA’s national estimates of the number and percentage of airports that used airfield pollution prev ention practices. See Section 7.4 for detailed descriptions of the pollution prev ention practices used by airports.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry

40 

### Table 4-10. Summary of Airfield Po llution Prevention Practices

Pollution Prevention Practice Estimated Number of Airports Using Practice Percentage of Airports Using Practice Specialized employee training 153 46
Pretreatment of airfield in advance of precipitation 101 30 Runway ice detecti on system 95 28 Enhanced weather forecasting 77 23
Heated sand 74 22 Evaluation of application rates of deicing fluids 56 17
Use of alternative chemicals 40 12 Use of prewet dry chemical constituents 32 10
Other 88 26 Source: EPA airport questionnaire database (scaled to national estimates) (USEPA, 2000c).



### Airlines also implement pollution prevention pr actices at various airports. These practices control pollution from aircraft deicing chemicals and minimize pollutant loads. Specialized training, implementation of a pollution preventi on policy, and physical snow removal are the most common pollution prevention practices used by airlines. Table 4-11 summarizes airline pollution prevention practices reported in respon se to the airline detailed questionnaire. See Section 7.4 for detailed descriptions of the po llution prevention practices used by airlines.

Table 4-11. Summary of Aircraft Pollution Prevention Practices

Pollution Prevention Practice Number of Airlines Reporting Practice Specialized employee training 43 Instituting pollution prevention policy 43 Physical removal of snow or freezing precipitation 31 Overnight pretreatment/storage of aircraft 30 Custom fluid blending 27 Enhanced weather forecasting 25 Evaluation of application rates of deicing fluids 24 Pretreating aircraft with hot water 9
Use of alternative chemicals 2
Other 30 Source: EPA airline detailed questio nnaire database (USEPA, 2008b).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 4 – Overview of the Industry

41 

### 4 .3 References

USDOT. 2008a. Report to Congress: National Plan of Integrated Airport Systems (NPIAS) 2009-2013 . U.S. Department of Transportation, Federal Aviation Administration. Washington, D.C. Available online at http://www.faa.gov/airports_airtraffic/ai rports/planning_capacity/npias/reports/.

USDOT. 2008b. FAA Regional Offices. U.S. Department of Tran sportation, Federal Aviation Administration. Washington, D. C. Available on line at www.faa.gov/about/office_org/headquarters_offices/arp/regional_offices/

.
USEPA. 2000. Preliminary Data Summary: Airport Deicing Operations. U.S. Environmental Protection Agency. Washington, D.C. EPA-821 -R-00-016. DCN AD00005. Available online at http://www.epa.gov/guide/airport.

USEPA. 2005. Supporting Statement: Survey of Airport Deicing Operations. U.S. Environmental Protection Agency/Office of Water. Washington, D.C. DCN AD00447.

USEPA. 2008a. Airline Screener Deici ng Questionnaire Database. U.S. Environmental Protection Agency. Washington, D.C. DCN AD00937.

USEPA. 2008b. Airline Detailed Deicing Questionnaire Database. U.S. Environmental Protection Agency. Washington, D.C. DCN AD00938.

USEPA. 2008c. Airport Deicing Questionnaire Database. U.S. Environmental Protection Agency. Washington, D.C. DCN AD00927.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 5 – Deicing Chemical Use and Deicing Stormwater Characterization

42 

### 5

. D EICING 

### C HEMICAL 

### U SE AND 

### D EICING 

### S TORMWATER 

### C HARACTERIZATION



### This section summarizes EPA’s estimate of the amount of airfield and aircraft deicing/anti-icing chemicals currently in use by U.S. primary commercial airports and provides information on deicing stormwater pollutant char acteristics to the extent possible. Deicing stormwater discharges are “weather-dependent” and they are, by nature, highly variable. In addition, deicing chemical disposition after it s intended use is not fully understood. These chemicals may be lost to evapora tion, dispersion, or soil absorption; collected; or released into the environment and discharged from the airport, but limited information is currently available on each of these disposition methods. This secti on presents the information EPA has collected on the types of pollutants present in deicing stormwater and th eir ranges of co ncentrations.

5 .1 Deicing Chemical Usage

As discussed in Section 4, several deicing chemicals are commonly used at U.S. commercial airports. These chemicals are used for either airfield or aircraft deicing/anti-icing and their usages are described below.

5 .1.1 Airfield Chemical Use

Pavement deicing/anti-icing removes or preven ts frost, snow, or ice from accumulating on runways, taxiways, aprons, gates, and ramps. Airports use mechanical and chemical methods for this purpose. The more often-used method is m echanical removal, but because ice, sleet, and snow may be difficult to remove by mechanical methods alone, many airports also use sand and/or chemical deicing agents such as potas sium acetate, sodium acetate, sodium formate, glycol-based products, or urea. Based on the data collected by EPA in the airport questionnaire, the most common airfield deicing chemical currently used by U.S. airports is potassium acetate (approximately 63 percent of airfield chemical usage by weight). Section 9, Table 9-6 presents the average amount of pavement deicing chemi cal usage in pounds per year by airport and by deicing chemical.

Table 5-1 lists the total estimated national average airfield chemical usage (based on data for the 2002/2003, 2003/2004, and 2004/2005 deicing season s) for primary commercial airports in the United States.

Table 5-1. U.S. Commercial Airports – Nation al Estimate of Airfield Chemical Usage

Chemical Estimated Total Airport Usage (tons/year) Percentage of Chemical Usage
Potassium acetate 22,538 63 Propylene glycol-based fluids 3,883 11
Airside urea 4,127 12
Sodium acetate 3,100 9
Sodium formate 1,117 3 Ethylene glycol-based fluids 774 2 Source: EPA Airport Deicing Questionnaire Database (USEPA, 2008a)Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 5 – Deicing Chemical Use and Deicing Stormwater Characterization

43 

### 5.1.2 Aircraft Chemical Use and Purchasing Patterns

There are four types of ADFs manufactured around the world, referred to by the aviation and chemical industries as Types I through IV. Of these, Type I and Type IV are commonly used at U.S. commercial airports. Type I ADF is used to defrost and deice aircraft and Type IV ADF is used to prevent icing from recurring (anti-icin g) after initial deicing with a Type I ADF. ADFs contain a primary freezing point depressant (typically PG or EG) and other additives. ADFs work by adhering to aircraft surfaces to rem ove and/or prevent snow and ice accumulation by virtue of their depressed freezi ng points. Airports conduct two types of deicing: dry-weather deicing to remove frost and wet-weather deici ng and anti-icing during precipitation such as snow, sleet (ice pellets), or fr eezing rain. Airports may also perform dry-weather deicing on some types of aircraft whose fuel tanks b ecome super-cooled during high-altitude flight, allowingfrost/ice to form on aircra ft wings at lower altitudes and after landing. Based on the data collected by EPA in the airline detailed ques tionnaire, the most common ADF is Type I PGbased fluids (approximately 77 percent of ADF us age). In addition, U.S. airports have been trending towards using more PG-based fluids and less EG-based fluids. Table 9-3 in Section 9 presents EPA’s estimates of ADF annual usage by airport based on the airline questionnaire responses and the estimation proced ure outlined in that section.

Table 5-2 presents a national estimate of the av erage aircraft chemical usage by U.S. commercial airports by type of fluid.

Table 5-2. U.S. Commercial Airports – Nation al Estimate of Aircraft Chemical Usage 1

Chemical Average Total Airport Usage (million gallons/year) 2 Percentage of Chemical Usage Type I PG ADF 19.305 77.1 Type IV PG ADF 2.856 11.4 Type I EG ADF 2.575 10.3 Type IV EG ADF 0.306 1.2 Sources: EPA Detailed Airline Questionnaire (USEPA, 200 8b); Airport Deicing Loadings Database (USEPA, 2008c).
1 EPA used the ADF purchase information to represent usage, per airline industry recommendations.
2 Total gallons normalized to 100% PG/EG.



### 5.2 De icing Stormwater Characterization

EPA evaluated data from a variety of s ources to better understand the components of deicing chemicals and ADFs that collect in deicing stormwater. These data include:

• 

### In formation on the additives included in ADFs;

• 

### Da ta collected during sampling of concen trated and diluted ADFs used at the Detroit Metropolitan Wayne County (DTW) and Minneapolis/St. Paul International (MSP) airports dur ing the 2003/2004 deicing season;

• 

### D ata collected during sampling of deicing stormwater at the Albany International (ALB), Pittsburgh International (PIT), Denver International (DEN), and Greater Rockford (RFD) airports duri ng the 2004/2005 deic ing season;Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 5 – Deicing Chemical Use and Deicing Stormwater Characterization

44 

### • 

### Cu rrent data for airports incl uded in the PCS database; and

• 

### Deicing stormwater data collected by EP A during the PDS, through site visits, or through industry or permit authority submissions.

Section 6 summarizes the types of pollutants found in deicing stormwater based on these

sources.

5 .2.1 Airfield Deicing Chemicals and As sociated Deicing Stormwater

Most solid airfield deicing chemical products comprise a freezing point depressant (e.g., potassium acetate, sodium acetate) and minimal additives (e.g., corrosion inhibitors). Liquid airfield deicing chemical products comprise a freezing point depressant (e.g., potassium acetate, PG), water, and minimal additives. The airfie ld deicing products that include salts (i.e., potassium acetate, sodium acetate, and sodium fo rmate) will ionize in water, creating positive salt ions (K + 

### , Na + 

### ) and BOD load as the acetate or formate ion degrades into carbon dioxide (CO 2 

### ) and water.

Urea is typically applied to pavement and r unway areas in granular form. Urea degrades by hydrolysis to CO 2 

### and ammonia, which can be toxic to aquatic organisms even at very low concentrations. Once ammonia is formed, it either remains in solution as ammonia or its ionized form (NH 4 + 

### ), biologically converts to other nitrogen forms (e.g., NO 3 

### or N 2 

### ), or volatilizes to the air. The formation of ammonia is dependent on th e pH and temperature of the receiving water. The higher the pH and temperature, the more a mmonia is formed. Anothe r potentially toxic byproduct of urea degradation is nitrous acid, whic h reacts with secondary amines to form nitrosamines, many of whic h are known carcinogens.

EPA has limited data on airfield deicing stormwater alone (i.e ., stormwater that does not also contain aircraft deicing area stormwater). Most of EPA’s stormw ater data include both airfield and aircraft deicing components. Ho wever, during sampling at DTW, EPA collected samples from the airport’s runway and open area ponds (Pond 3 East and Pond 6). These ponds are not expected to contain aircraft deicing stormwater because a separate pond collects wastewater from the gate and deicing pad areas where the stormwater is expected to contain ADF. DTW sometimes uses sand and potassium acetate for runway traction and deicing in addition to their usual mechanical snow removal equipment. It doe s not use urea-based deicers.

Table 5-3 presents the sampling data from the two airfield/o pen area runoff ponds.

5 .2.2 Aircraft Deicing Chemicals and Associated Deicing Stormwater

ADFs primarily comprise a freezing point depres sant (typically PG or EG), additives, and water. Typical additives are thickening agents, wetting agents, corrosion inhibitors, buffer, and dye, which make up 1 to 4 percent of the fluid ma ss. Type IV fluids have higher concentrations of the freezing point depressant a nd greater viscosity so that the fluid stays on the aircraft until take-off.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 5 – Deicing Chemical Use and Deicing Stormwater Characterization

45 

### Table 5-3. EPA’s Analytical Results for Po nd 3E Effluent and Pond 6 Effluent, DTW

Analyte Unit Pond 3 East Effluent Pond 6 Effluent
BOD 5 mg/L 146 43.0
Chloride mg/L 855 315
COD mg/L 273 111 Nitrate/Nitrite (NO 2 + NO 3 -N) mg/L 0.0400 0.110
Sulfate mg/L 50.1 51.0 Total Dissolved Solids (TDS) mg/L 1,790 833 Total Kjeldahl Nitrogen (TKN) mg/L 1.51 0.990
TOC mg/L 813 314 Total Phosphorus mg/L 0.340 0.280
TSS mg/L 150 149
Aluminum μ g/L 1,660 2,110 Aluminum, Dissolved μ g/L ND (50.0) 64.5
Barium μ g/L 92.3 81.8 Barium, Dissolved μ g/L 77.5 66.5
Calcium μ g/L 96,600 69,400 Calcium, Dissolved μ g/L 91,000 63,500
Chromium 1 μ g/L ND (10.0) ND (10.0) Copper 1 μ g/L ND (10.0) ND (10.0)

Iron μ g/L 3,630 4,390 Iron, Dissolved μ g/L 407 600 Magnesium μ g/L 20,300 17,400 Magnesium, Dissolved μ g/L 18,200 15,700 Manganese μ g/L 508 411 Manganese, Dissolved μ g/L 462 335 Molybdenum μ g/L ND (10.0) ND (10.0) Molybdenum, Dissolved μ g/L ND (10.0) ND (10.0)
Sodium μ g/L 547,000 191,000 Sodium, Dissolved μ g/L 522,000 189,000
Titanium μ g/L 26.2 34.8
Zinc 1 μ g/L 41.4 43.8
Acetone μ g/L ND (50.0) ND (50.0)
PG - 1671 2 mg/L ND (10.0) ND (10.0)
PG - 8015D 2 mg/L ND (10.0) ND (10.0) Source: Final Sampling Episode Report Detroit Metropo litan Wayne County Internatio nal Airport (DTW) (USEPA, 2006a).
1 Pollutant listed by EPA as a priority pollutant. See 40 CFR Part 423, Appendix A.
2 Number following analyte name refers to analytical method. 1671 is a Clean Water Act method and 8015D is a hazardous waste met hod promulgated under the Resource C onservation and Recovery Act (RCRA). ND – Not detected (number in parentheses is reporting limit).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 5 – Deicing Chemical Use and Deicing Stormwater Characterization

46 

### The actual composition of ADFs varies and information on specific additive compounds is usually considered propriet ary by ADF manufacturers. EPA be lieves that typical ADFs most likely include the following components:

ADF Component Composition (%)
PG or EG 50-88 Surfactant/wetting agent About 0.5
Corrosion inhibitor/flame retardant About 0.5 pH buffer About 0.25 Dyes <1
Water Remainder
Source: Environmental Impact and Benefit Assessment for Propos ed Effluent Limitations Guidelines and Standards for the Airport Deicing Category (ERG, 2009).



### Despite limited public information, EPA has id entified two main classes of additives widely used among ADF manufacturers. Alkylph enol/alkylphenol ethoxylates (AP/APEO) are nonionic surfactants used to reduce surface tension in aircraft deicer s and triethanolamine is used as a pH buffer. (ERG, 2009). At th e time of proposal of the rule , EPA also identified methylsubstituted benzotriazole (MeBT) as an ADF additive, which was used as a corrosion inhibitor/flame retardant. In conversations with ADF manufacturers since proposal, EPA has been told that the use of tri azole compounds in ADF is being di scontinued and that triazole use in European ADFs has been phased out. EPA also has information indicati ng that high molecular weight, nonlinear polymers may be used as thickening agents in ADFs (see Aircraft Deicing Fluids (ERG, 2007b) and various classes of dyes can be used to color th e ADF. The classes of dyes identified as potentially used in ADFs in clude azo, xanthene, triphenyl methane, and anthroquinone dyes (see Questions Regarding Pylam Dye Use in ADF (ERG, 2007a).

Analyses conducted by the USGS at General Mitchell International (MKE) airport in Milwaukee, WI, and EPA’s sampling programs have confirmed the presence of glycols, triazole compounds, and alkylphenol compounds in de icing stormwater. EPA collected deicing stormwater samples at MSP and DTW duri ng the 2004/2005 winter season. At MSP, EPA collected samples of deicing stormwater fr om segregated high concentration and low concentration storage tanks. At DTW, Northwest collected its deicing st ormwater from a March 24, 2005 deicing event into a portable “frac” tank, which was then sampled by EPA. Table 5-4 lists the constituents detected in these deicing stormwaters and their concentrations. During the 2005/2006 deicing season, EPA collected five consecutive days of samples of influent to and effluent from deicing stormwater treatment at ALB, PIT, DEN, and RFD. The sampled deicing stormwater at these airports, prior to treatm ent, shows a wide range of constituents and constituent concentrations am ong the airports, as shown in Table 5-5 and Table 5-6

.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 5 – Deicing Chemical Use and Deicing Stormwater Characterization

47 

### Table 5-4. MSP and DTW Grab Sample Data Summary for Collected Deicing Stormwater

Analyte Unit MSP High Concentration Storage Tank MSP Low Concentration Storage Tank DTW Northwest Frac Tank
Classical Pollutants Ammonia as Nitrogen (NH 3 -N) mg/L ND (0.05) ND (0.05) 0.790
BOD 5 mg/L 115,000 8,000 140,000
Chloride mg/L 45.0 27.0 25.0
COD mg/L 358,000 16,000 332,000 Hexane Extractable Material (HEM) mg/L 50.0 ND (5.00) 22.0 Nitrate/Nitrite (NO 2 + NO 3 -N) mg/L 0.0950 <0.0600 0.240 Silica Gel Treated HEM (SGT-HEM) mg/L 17.0 ND (5.00) ND (6.00)
Sulfate mg/L 21.2 13.6 20.3
TDS mg/L 1,370 559 1,440
TKN mg/L 13.5 5.61 71.1
TOC mg/L 96,100 5,660 93,100 Total Phosphorus mg/L 6.49 < 2.10 0.320
Total Recoverable Phenolics mg/L 0.150 0.0375 <0.007
TSS mg/L 89.0 19.5 11.5
Total and Dissolved Metals
Aluminum μ g/L 525 508 ND (500) Aluminum, Dissolved μ g/L ND (500) 136 ND (500) Antimony, Dissolved 1 μ g/L 201 ND (20.0) ND (200)
Barium μ g/L 114 67.1 52.4 Barium, Dissolved μ g/L 36.4 61.9 46.9
Calcium μ g/L 68,200 35,200 127,000 Calcium, Dissolved μ g/L 59,600 34,500 125,000 Copper 1 μ g/L ND (100) 37.6 ND (100) Copper, Dissolved 1 μ g/L ND (100) 16.4 ND (100)
Iron μ g/L 11,000 7,470 1,410 Iron, Dissolved μ g/L 4,960 6,030 1,370 Magnesium μ g/L 9,230 4,250 12,900 Magnesium, Dissolved μ g/L 8,490 4,080 13,000 Manganese μ g/L 887 317 433 Manganese, Dissolved μ g/L 756 308 423 Mercury 1 μ g/L ND (40) ND (2) 45.1 Mercury, Dissolved 1 μ g/L ND (40) ND (2) 68.7 Molybdenum μ g/L 19,100 794 15,900 Molybdenum, Dissolved μ g/L 19,000 771 16,000
Sodium μ g/L 48,700 18,700 22,800 Sodium, Dissolved μ g/L 48,100 18,600 19,200
Tin μ g/L 611 32.1 673Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 5 – Deicing Chemical Use and Deicing Stormwater Characterization



### Table 5-4 (Continued)

48 Analyte Unit MSP High Concentration Storage Tank MSP Low Concentration Storage Tank DTW Northwest Frac Tank Tin, Dissolved μ g/L 616 32.5 646
Titanium μ g/L ND (100) 13.5 ND (100)
Zinc 1 μ g/L 492 291 119 Zinc, Dissolved 1 μ g/L 444 277 119 Volatile and Semivolatile Organics
Acetone μ g/L 1,440 23,700 3,340
PG – 1671 2 mg/L — — 192,000
PG – 8015D 2 mg/L 193,000 8,600 170,000
Trichloroethene 1 μ g/L ND (10) ND (10) 14.5

Sources: Final Sampling Episode Report Minneapolis/St. Paul International Airport (MSP) (USEPA, 2006b); Final Sampling Episode Report Detroit Metropolitan Wayne C ounty International Airpor t (DTW) (USE PA, 2006a).
1 Pollutant listed by EPA as a priority pollutant. See 40 CFR Part 423, Appendix A.
2 Number following analyte name refers to analytical method. 1671 is a Clean Water Act method and 8015D is a hazardous waste met hod promulgated under the Resource C onservation and Recovery Act (RCRA). < – Average result includes at least one nondetect value. ND – Not detected (number in parenthesis is reporting limit).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 5 – Deicing Chemical Use and Deicing Stormwater Characterization

49 

### Table 5-5. DEN, PIT, and ALB - 5-Day Aver age Data Summary for Untreated Deicing Stormwater

Analyte Units DEN Effluent from Equalization Feed Tank 5-day Average PIT Influent to Reverse Osmosis (RO) Unit 5-day Average ALB Influent to Anaerobic Treatment System 5-day Average Alkalinity mg/L 706 481 159

NH 3 -N) mg/L 0.448 ND (0.05) <0.262
BOD 5 mg/L 149,000 16,600 3,400
COD mg/L 247,000 28,300 5,350
Chloride mg/L 120 11.6 90.0
Hardness mg/L 362 542 248

HEM mg/L 9.20 ND (6.0) ND (5.0)

NO 3 -N + NO 2 -N) mg/L 0.0266 <0.0204 <0.0284
Sulfate mg/L 60.0 48.1 26.4
TDS mg/L NC 1,670 650

TKN mg/L 6.41 9.04 1.61
TOC mg/L 89,000 7,720 1,570 Total Orthophosphate mg/L <1.03 <0.0196 0.115 Total Phosphorus mg/L <2.76 0.0778 0.946
Total Recoverable Phenolics mg/L 0.0608 0.0187 ND (0.005)

TSS mg/L <17.8 <8.40 16.6
Arsenic μ g/L <81.8 12.7 ND (10)
Barium μ g/L <13.2 103 42.5

Boron μ g/L <723 532 ND (100)
Calcium μ g/L 103,000 155,000 48,300 Copper μg/L 305 ND (10) ND (10)

Iron μ g/L 1,210 5,870 6,270 Magnesium μ g/L 5,360 6,260 9,990 Manganese μ g/L 156 532 736 Molybdenum μg/L 11,900 ND (10) ND (10)
Selenium μ g/L 172 31.8 <5.38
Sodium μ g/L 254,000 54,300 89,600
Tin μ g/L <258 41.0 ND (30)
Zinc μ g/L <81.1 71.8 48.3
Acetone μ g/L 4,100 10,900 15,400
Benzoic Acid μ g/L 716 ND (50) 278 Methyl Ethyl Ketone μ g/L ND (50) ND (50) <58.5
Phenol μ g/L ND (100) ND (100) 24.5

EG - 1671 1 mg/L <167 <65.6 ND (10)

EG - 8015D 1 mg/L <172 <73.6 ND (10)Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 5 – Deicing Chemical Use and Deicing Stormwater Characterization



### Table 5-5 (Continued)

50 Analyte Units DEN Effluent from Equalization Feed Tank 5-day Average PIT Influent to Reverse Osmosis (RO) Unit 5-day Average ALB Influent to Anaerobic Treatment System 5-day Average
PG - 1671 1 mg/L 174,000 15,700 2,570
PG - 8015D 1 mg/L 173,000 15,900 2,630 Tolyltriazole μ g/L 10,100 7,860 325 Nonylphenol, total μ g/L ND (5.0) 22.2 ND (12.0) Nonylphenol-1-Ethoxylate μ g/L ND (7.4) 130 ND (19.0) Nonylphenol-2-Ethoxylate μ g/L ND (21.0) 190 ND (53.0) Nonylphenol-3-Ethoxylate μ g/L 17.8 59.9 3.90 Nonylphenol-4-Ethoxylate μ g/L 16.4 15.4 3.01 Nonylphenol-5-Ethoxylate μ g/L 21.5 213 5.70 Nonylphenol-6-Ethoxylate μ g/L 50.4 403 12.5 Nonylphenol-7-Ethoxylate μ g/L 60.7 619 15.4 Nonylphenol-8-Ethoxylate μ g/L 86.2 841 24.7 Nonylphenol-9-Ethoxylate μ g/L 79.1 942 24.7 Nonylphenol-10-Ethoxylate μ g/L 92.5 1,050 38.1 Nonylphenol-11-Ethoxylate μ g/L 100 1,040 40.4 Nonylphenol-12-Ethoxylate μ g/L 216 833 33.7 Nonylphenol-13-Ethoxylate μ g/L 167 589 25.2 Nonylphenol-14-Ethoxylate μ g/L 116 386 17.8 Nonylphenol-15-Ethoxylate μ g/L 69.9 222 8.80 Nonylphenol-16-Ethoxylate μ g/L 43.4 107 4.69 Nonylphenol-17-Ethoxylate μ g/L 23.3 53.5 2.27 Nonylphenol-18-Ethoxylate μ g/L 12.4 23.3 1.09 Octylphenol μ g/L <8.80 ND (0.01) ND (2.00) Octylphenol-2-Ethoxylate μ g/L 71.8 ND (0.144) 0.159 Octylphenol-3-Ethoxylate μ g/L 1,460 4.38 2.66 Octylphenol-4-Ethoxylate μg/L 1,260 ND (2.26) ND (2.26) Octylphenol-5-Ethoxylate μg/L 891 ND (2.93) ND (2.93) Octylphenol-6-Ethoxylate μg/L 441 ND (2.69) ND (2.69) Octylphenol-7-Ethoxylate μg/L 198 ND (2.58) ND (2.58) Octylphenol-8-Ethoxylate μg/L 116 ND (1.85) ND (1.85) Octylphenol-9-Ethoxylate μg/L 44.6 ND (0.636) ND (0.636) Octylphenol-10-Ethoxylate μg/L 22.5 ND (0.636) ND (0.636) Octylphenol-11-Ethoxylate μg/L 12.0 ND (0.267) ND (0.267) Octylphenol-12-Ethoxylate μg/L 8.08 ND (0.113) ND (0.113)Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 5 – Deicing Chemical Use and Deicing Stormwater Characterization



### Table 5-5 (Continued)

51 Analyte Units DEN Effluent from Equalization Feed Tank 5-day Average PIT Influent to Reverse Osmosis (RO) Unit 5-day Average ALB Influent to Anaerobic Treatment System 5-day Average Total Nonylphenol-3- Ethoxylate-Nonlyphenol-18- μ g/L 1,170 7,400 260

Total Octylphenol-2-EthoxylateOctylphenol-12-Ethoxylate μg/L 4,530 ND (16.0) ND (16.0)

Sources: Draft Sampling Episode Report Denver Interna tional Airport (USEPA, 2006c); Draft Sampling Episode Report Pittsburgh International Airp ort (USEPA, 2006d); Draft Sampling Ep isode Report Albany International Airport (USEPA, 2006e).
1 Number following analyte name refers to analytical method. 1671 is a Clean Water Act method and 8015D is a hazardous waste met hod promulgated under the Resource C onservation and Recovery Act (RCRA). ND – Not detected (number in parentheses is reporting limit). NC – Not collected. < – Average result includes at least one nondetect value.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 5 – Deicing Chemical Use and Deicing Stormwater Characterization

52 

### Table 5-6. RFD - 1-Day Data Summary for Untreated Deicing Stormwater

Analyte Units Influent to Aerobic Treatment System, Spring Alkalinity mg/L 1,030
NH 3 -N mg/L 59.6
BOD 5 mg/L 603
COD mg/L 646
Chloride mg/L 14.0
Hardness mg/L 112
NO 3 -N + NO 2 -N) mg/L 0.0190
Sulfate mg/L 5.65
TDS mg/L 384
TKN mg/L 82.8
TOC mg/L 137 Total Phosphorus mg/L 0.330
TSS mg/L 85.0
Barium μ g/L 20.3
Calcium μ g/L 6,600
Iron μ g/L 108 Magnesium μ g/L 14,700 Manganese μ g/L 164
Sodium μ g/L 4,790
Acetone μ g/L 86.6 Methyl Ethyl Ketone μ g/L 136
PG - 8015D 1 mg/L 31.0 Tolyltriazole μ g/L 45.3 Bisphenol A ng/L ND (12,000) N-Nonylphenol-2-Ethoxylate NC 50.0 N-Nonylphenoxyl-2-Carboxylic Acid NC 41.0 Octylphenol-9-Ethoxylate μ g/L ND (3.18) Source: Final Sampling Episode Report Greater Rockford Airport (USEPA, 2006f)
1 Number following analyte name refers to analytical method. 8015D is a hazardous waste method promulgated under the Resource Conservation and Recovery Act (RCRA). ND – Not detected (number in parentheses is reporting limit).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 5 – Deicing Chemical Use and Deicing Stormwater Characterization

53 

### 5 .3 Aircraft and Airfield Deicing Chemical Use and Associated Deicing Stormwater at Alaskan Airports

Deicing operations at Alaskan airports may be different than those commonly seen at other U.S. airports due to the na ture of air travel in Alaska and weather conditions. In Alaska, small airports have a relatively high number of commercial aircraft departures (including jet aircraft) for the suite of communities they serve due to their remote locations with no access to the road system. Yet these airpor ts utilize small amounts of ADF and runway deicers because of climate conditions (dry and cold), as well as runway maintenance scheduling. For example, in Kotzebue, a town of 3,120 people, there are a bout 12,000 annual departures (including passenger and freight jet planes and prop planes) and the fluid usage is only about 1,000 gallons/winter.

In addition, long periods of be low-freezing temperatures affect the the timing of deicing stormwater discharges. Deici ng materials are not available for collection during freezing temperatures because they are encapsulated w ithin the snow and eventually become runoff during the spring thaw. Thus, the stormwater ru noff is not linked to the time of the ADF application. For example, at locatio ns in arctic Alaska such as Bethel Airport (BET), there is no stormwater to collect during the deicing season (October – March) as te mperatures rarely, if ever, go above freezing. For these airports, collecti on strategies may be significantly different than airports located within the lower 48 stat es. One current practice reported by Ted Stevens Anchorage International Airport (ANC) is gas- and-go cargo operations, which involves antiicing on landing during certain weat her conditions. This allows the airport to avoid deicing prior to departure. This anti-icing procedure also us es less glycol and allo ws a quicker turnaround.

Due to the remote nature of Alaskan air ports and aircraft scheduling, runways are generally prepped for individual flights each da y rather than maintaining continuous operation around the clock. Because of this, Alaskan airpor ts rely heavily on mechanical methods for runway deicing. When airfield deicing chemical use is necessary, most airports in Alaska use potassium acetate or urea.

5 .4 References

Corsi, S.R., et al. 2003. Nonylphenol Ethoxylates and Other Add itives in Aircraft Deicers, Antiicers, and Waters Receiving Airport Runoff. (January 1). DCN AD00083.

ERG. 2007a. Personal communication (telecon ) between Mary Willett (ERG) and Bob Reynolds (Pylam Dyes). Questions Regarding Pylam Dye Use in ADF . (April 16). DCN AD00686.

ERG. 2007b. Personal co mmunication (telecon) between Mary Willett (ERG) and Jeffery Carey (Noveon). Aircraft Deicing Fluids . (April 16). DCN AD00688.

USEPA. 2006a. Final Sampling Episode Report De troit Metropolitan Wayne County International Airport (DTW), Episode 6508. U.S. Environmental Protection Agency. Washington, D.C. (July 12). DCN AD00620.

USEPA. 2006b. Final Sampling Episode Report Minneapolis /St. Paul International Airport (MSP), Episode 6509 . U.S. Environmental Protection Agen cy. Washington, D.C. (July 12). DCN AD00622.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 5 – Deicing Chemical Use and Deicing Stormwater Characterization

54 

### USEPA. 2006c. Final Sampling Episode Report Denver International Airport, Episode 6522. U.S. Environmental Protection Agency. Washington, D.C. (August 2). DCN AD00840.

USEPA. 2006d. Final Sampling Episode Report Pittsburgh International Airport, Episode 6528. U.S. Environmental Protection Agency. Washington, D.C. (November 1). DCN AD00841.

USEPA. 2006e. Final Sampling Episode Report Albany International Airport, Episode 6523. U.S. Environmental Protection Agency. Washington, D.C. (July 19). DCN AD00842.

USEPA. 2006f. Final Sampling Episode Report Greater Rockford Airport, Sampling Episode 6529 (April 20, 2006) and Sampling Episode 6530 (August 29, 2006, January 18, 2008). U.S. Environmental Protection Agenc y. Washington, D.C. DCN AD00839.

USEPA. 2008a. Airport Deicing Questionnaire Database. U.S. Environmental Protection Agency. Washington, D.C. DCN AD00927.

USEPA. 2008b. Airline Questionnaire Database. U.S. Environmental Protection Agency. Washington, D.C. DCN AD00938.

USEPA. 2008c. Airport Deicing Loadings Database. U.S. Environmental Protection Agency. Washington, D.C. DCN AD00857.

USEPA. 2009. Environmental Impact and Benefit Assess ment for Proposed Effluent Limitation Guidelines and Standards for the Airport Deicing Category. (July 1). EPA 821-R-09-005. DCN AD01197.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 6 – Pollutants of Concern

55 

### 6

. P OLLUTANTS OF 

### C ONCERN


### EPA identified pollutants in stormwater associ ated with deicing ac tivities for potential control. Pollutants of concern may include pollutants directly asso ciated with deicing chemicals, by-products from deicing activities (e.g., metals), a nd/or pollutant parameters that are influenced by deicing chemicals (e.g., BOD and COD).

EPA reviewed its deicing stormwater sampling data as well as the information available through NPDES permits to identify conventional, nonconventional, and pr iority pollutants present in airport deicin g stormwater. This section presents the results of EPA’s evaluation and identifies potential pollu tants of concern and those chosen for regulation.

6 .1 Identification of Airport Deicin g/Anti-icing Stormwater Pollutants

Airport deicing stormwater is generated when airfield de icing chemicals and ADFs mix with stormwater (either directly or because of snowmelt). Because deicing stormwater is weather-dependent, it is highly va riable in nature and pollutant concentrations may vary greatly. In addition, other airport-related activities, including aircraft fue ling and maintenance activities, may contribute pollutants to stor mwater that is also contamin ated with deicing chemicals. Because of the inherent difficulties in characte rizing pollutants resulting solely from deicing activities, EPA evaluated pollutants detected in deicing stormwater, pollu tants present in source water, and pollutants that are present in ADFs and airfield deicers prior to use to determine the pollutants likely to be pres ent in deicing stormwater.

EPA considered multiple sources of information to identify potential pollutants of concern associated with deicing st ormwater including the following:

• 

### EPA sampling data from the PDS;

• 

### NPDES permits for airports to determine pollutants that are currently monitored or limited at airports;

• 

### EPA sampling data collected dur ing the 2004/2005 and 2005/2006 deicing seasons to identify pollutants presen t in untreated deicing stormwater;

• 

### EPA sampling data collected dur ing the 2004/2005 and 2005/2006 deicing seasons to determine pollutants present in source water;

• 

### EPA sampling data collected during the 2004/2005 deici ng season, current research, and expert sources to determine ADF constituents; and

• 

### Responses to the airport questionnaire.

Airport Deicing Operations PDS

For the PDS, EPA sampled:

• 

### Type I ADFs;

• 

### Lagoon stormwater from Albany International Airport;

• 

### Untreated deicing stormwater from Ka nsas City Internat ional Airport;

• 

### Untreated deicing stormwater from Bradley International Airport;

• 

### Untreated deicing stormwater from Greater Rockford Airport; and

• 

### Stormwater outfalls from Brad ley International Airport.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 6 – Pollutants of Concern

56 

### The pollutants detected in one or more of th ese samples were summarized in Table 8-4 of the Preliminary Data Summary: Airport Deicing Operations report (USEPA, 2000) and are presented in Table 6-1 of this report.

NPDES Permits

EPA reviewed NPDES individual and general st ormwater permits for airports that are estimated to have significant deicing operations in the United States. The permit review is summarized in the Airport Deicing Operations NPDES Permit Review Summary memorandum (ERG, 2007a). Table 6-1 lists pollutants that have monitoring and limit requirements in current airport NPDES permits.

Pollutants Present in Untreated Deicing Stormwater

Under this rulemaking effort, EPA collected samples at the following six airports during the 2004/2005 and 2005/2006 deicing seasons:

• 

### Detroit Metropolitan Wayne County (DTW) airport;

• 

### Minneapolis/St. Paul International (MSP) airport;

• 

### Albany International (ALB) airport;

• 

### Greater Rockford (RFD) airport;

• 

### Pittsburgh International (PIT) airport; and

• 

### Denver International (DEN) airport.

Table 6-1 lists pollutants detected in untreated deicing stormwater from these locations.

Pollutants Present in Source Water

Table 6-1 also lists pollutants detected in s ource water samples at the airports EPA sampled at during the 2004/ 2005 and 2005/2006 deicing seasons.

Deicing/Anti-Icing Fluid Constituents

EPA does not have sufficient information on all of the constituents of airfield chemicals and ADFs to fully characterize them. However, EP A’s airport questionnaire does identify which chemicals and brand-name products are commonly used, which can help to define the pollutants expected to be in deicing stormwater.57Technical Development Document for EffluentLimitation Guidelines and Standards for the Airport Deicing CategorySection 6 – Pollutants of ConcernTable 6-1. Pollutants Under Considerationas Potential Pollutants of ConcernAnalytePollutantsIdentified inthe PDSSamplingPollutantsMonitored inNPDESPermitsPollutants Identified inRaw ADF in Research or2004-2006 EPASamplingPollutants Identified inUntreated Stormwaterin 2004-2006 EPASamplingPollutants Identified inSource Water in 2004-2006 EPA SamplingClassicals/ConventionalsAlkalinityXXNH3-NXXXXBOD5XXXXCODXXXChlorideXXXDissolved OxygenXHardnessXXOil & GreaseXSGT-HEMXXHEMXXXNO3-N + NO2-NXXXSulfateXXXTDSXXTKNXXXTOCXXXXTotal OrthophosphateXXTotal PhosphorusXXXTotal Petroleum Hydrocarbons (TPH)XTotal Recoverable PhenolicsXXTSSXXMetalsAluminumXXAntimonyXXXArsenicXXXBariumXXXBoronXX58Technical Development Document for EffluentLimitation Guidelines and Standards for the Airport Deicing CategorySection 6 – Pollutants of ConcernTable 6-1 (Continued)AnalytePollutantsIdentified inthe PDSSamplingPollutantsMonitored inNPDESPermitsPollutants Identified inRaw ADF in Research or2004-2006 EPASamplingPollutants Identified inUntreated Stormwaterin 2004-2006 EPASamplingPollutants Identified inSource Water in 2004-2006 EPA SamplingCadmiumXCalciumXXXXChromiumXXCopperXXXXXIronXXXXLeadXXMagnesiumXXXXManganeseXXMercuryXXMolybdenumXXPotassiumXSeleniumXXSilverXSodiumXXXXThalliumXTinXXXTitaniumXVanadiumXZincXXXXXOrganicsAcetoneXXBenzene, toluene, ethylbenzene, xylene(BTEX)XXBenzoic AcidXBis(2-Ethylhexyl) PhthalateXDi-n-butyl PhthalateXDiethylene GlycolX59Technical Development Document for EffluentLimitation Guidelines and Standards for the Airport Deicing CategorySection 6 – Pollutants of ConcernTable 6-1 (Continued)AnalytePollutantsIdentified inthe PDSSamplingPollutantsMonitored inNPDESPermitsPollutants Identified inRaw ADF in Research or2004-2006 EPASamplingPollutants Identified inUntreated Stormwaterin 2004-2006 EPASamplingPollutants Identified inSource Water in 2004-2006 EPA SamplingN-DodecaneXEGXXXN-HexadecaneXMethyl Ethyl KetoneXNaphthaleneXPhenolXXPGXXXXN-TetradecaneX1,2,4- TrimethylbenzeneXTrichloroetheneXTolyltriazoleXBenzotriazole5-Methyl-1H-benzotriazoleXAlkylphenolsNonylphenol, totalXXNonylphenol-1-EthoxylateXXNonylphenol-2-EthoxylateXXNonylphenol-3-EthoxylateXXNonylphenol-4-EthoxylateXXNonylphenol-5-EthoxylateXXNonylphenol-6-EthoxylateXXNonylphenol-7-EthoxylateXXNonylphenol-8-EthoxylateXXNonylphenol-9-EthoxylateXXNonylphenol-10-EthoxylateXXNonylphenol-11-EthoxylateXXNonylphenol-12-EthoxylateXXX60Technical Development Document for EffluentLimitation Guidelines and Standards for the Airport Deicing CategorySection 6 – Pollutants of ConcernTable 6-1 (Continued)AnalytePollutantsIdentified inthe PDSSamplingPollutantsMonitored inNPDESPermitsPollutants Identified inRaw ADF in Research or2004-2006 EPASamplingPollutants Identified inUntreated Stormwaterin 2004-2006 EPASamplingPollutants Identified inSource Water in 2004-2006 EPA SamplingNonylphenol-13-EthoxylateXXXNonylphenol-14-EthoxylateXXXNonylphenol-15-EthoxylateXXXNonylphenol-16-EthoxylateXXXNonylphenol-17-EthoxylateXXXNonylphenol-18-EthoxylateXXXOctylphenolXXOctylphenol-2-EthoxylateXXOctylphenol-3-EthoxylateXXOctylphenol-4-EthoxylateXXOctylphenol-5-EthoxylateXXOctylphenol-6-EthoxylateXXOctylphenol-7-EthoxylateXXOctylphenol-8-EthoxylateXXOctylphenol-9-EthoxylateXXOctylphenol-10-EthoxylateXXOctylphenol-11-EthoxylateXXOctylphenol-12-EthoxylateXXTotal Nonylphenol-3-EthoxylateNonlyphenol-18-EthoxylateXXXTotal Octylphenol-2-EthoxylateOctylphenol-12-EthoxylateXXNote: Octylphenol and nonylphenol should have a higher toxicity than the alkylphenol ethoxylates.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 6 – Pollutants of Concern

61 

### The commonly used airfield deicing and anti-i cing chemicals are listed below, along with the approximate percentage of total airfield deicing chemical usage they comprise:

• 

### Potassium acetate (64 percent);

• 

### Propylene glycol-based fluids (12 percent);

• 

### Ur ea (11 percent);

• 

### Sodium acetate (9 percent);

• 

### Sodium formate (3 percent); and

• 

### Ethylene glycol-based fluids (2 percent).

EPA has two sources of data on the constituents of ADF. First, EPA collected and analyzed samples of unused, or “raw,” ADF du ring the sampling episodes at DTW and MSP. Table 6-1 lists the chemical compounds for which EP A analyzed the raw ADF samples. Second, EPA reviewed research conducted by USGS to determine potential ADF constituents. Steven Corsi of USGS conducts research and sampli ng on ADF and deicing stormwater at General Mitchell International Airport in Milwaukee, WI . He has published several papers presenting his research and sampling results and has identified the following pollutants in ADF stormwater and snowmelt:

• 

### BO D 5 

### ;

• 

### COD;

• 

### PG and EG;

• 

### AP and APEO; and

• 

### Benzotriazole (BT) and its met hylated derivatives (MeBT).

6 .2 Pollutants of Concern Selection Criteria

Having identified pollutants that are likely to be present in airpor t deicing stormwater, EPA then considered which pollutants should be pollutants of concern. EPA considered the following criteria in assessing poten tial pollutants of concern for the airport deicing industry:

• 

### Whether the pollutant can be directly linked to deicing/anti-icing chemicals;

• 

### Whether the pollutant is detected in the e ffluent from a small number of airports and is uniquely related to those facilities; or

• 

### Whether the pollutant can be analyzed using an EPA-approved or other established method.

After considering the criteria listed above, EP A developed a list of those pollutants that are considered potential pollutants of concern.

6 .3 Identification of Potential Pollutants of Concern

EPA compared the pollutants detected in deic ing stormwater to ADF and airfield deicer constituents and determined that many pollutants present in the stormwater are not present in ADF or airfield deicers. Stor mwater contains pollutants from sources other than ADF and airfield deicers; these sources may incl ude, but are not limited to, the following:

• 

### Source water pollutants (present in the wa ter used at the airport facility);

• 

### Pollutants from aircraft and vehicle fueling;Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 6 – Pollutants of Concern

62 

### • 

### Pollutants from maintenance-related operations; or

• 

### Pollutants from roof runoff.

EPA also considered the other criteria liste d in Section 6.2 to asse ss potential pollutants of concern. Below is a summary of EPA’s eval uation of potential pollutants of concern by the following analytical categorie s: classical/conventional para meters, metals, and organic pollutants.

Classical/Conventional Parameters

The major components of both airfield de icing chemicals and ADFs are organic and degrade in the environment after their release. Because of this, COD and BOD 5 

### concentrations are generally high in deicing stormwater. Both of these pollutant parameters are also good indicators of the amount of acetates, urea, glyc ols, and formates in deicing stormwater.

EPA believes that those airpor ts with discharge permits re quiring monitoring and control of ammonia, TKN, and nitrate/ nitrite are likely doing so to monitor discharges of urea. Information collected during EPA’s ai rport site visits seemed to i ndicate that airports have been phasing out the use of urea for airfield deicing. However, EPA’s analysis of urea use from the airport questionnaire showed an increase during the 2002/2003 through 2004/2005 deicing seasons, with approximately the same number of airports using urea in each of those seasons.

Several of the classical para meters detected in deicing stormwater are from nondeicing stormwater, dilution water, or other airport ope rations. Based on information on airfield deicers and analysis of raw ADF, EPA concludes these pollutants are not present in ADF or airfied deicers but are present in deic ing stormwater. Pollutants from airport sources aside from ADF/airfied deicers include alkalinity, har dness, oil and grease, TDS, and TSS.

Other classical/conventional parameters (inc luding chloride, TOC, and total phosphorus) are found in source water, which is used to di lute ADF/airfield deicer s prior to application. Therefore, EPA concluded these pollutants are not present in ADF/airfield deicers.

Finally, while total recoverable phenolics are present in EPA sampling results, the phenols in ADF are widely reported as alkylphenol s and octylphenols; ther efore, EPA chose the analyte-specific results and not the bulk paramete r as the more appropri ate indicator of phenols in ADF.

Metals

Multiple metals have been detected in samples of airport deicing stormwater. Some of these metals were also detected in the ADF samples collected by EPA. Many of these metals are not original components of deicing products (e.g., aluminum and seleniun); they are present as background concentrations from the stormwater or source water used for ADF dilution or they are metals picked up by stormwater runoff from ai rcraft maintenance/operation areas or building roofs.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 6 – Pollutants of Concern

63 

### Nonyl/Octyl-Phenol-Ethoxylates

EPA sampling data shows the presence of both nonylphenol and octylphenol ethoxylates. EPA decided to use the total octylphenol and total nonylphenol ethoxolates as the indicator for all ethoxolates.

Organic Pollutants

Organic pollutants present in deicing stor mwater include PG, EG, triazole compounds, alkylphenols, and alkylphenol ethoxylates. Other organics may also be present from the breakdown of glycols, urea, acetates, and formates.

Pollutants of Concern

Based on this evaluation of available data , EPA identified the following as potential pollutants of concern for th e Airport Deicing Category:

• 

### COD;

• 

### BOD5;

• 

### EG;

• 

### PG;

• 

### Benzotriazole;

• 

### 5-Methyl-1H-benzotriazole;

• 

### Nonylphenol, total;

• 

### Octylphenol, total;

• 

### Total nonylphenol-3-ethoxylate- nonlyphenol-18-ethoxylate;

• 

### Total octylphenol-2-ethoxylat e-octylphenol-12-ethoxylate;

• 

### Ammonia as nitrogen;

• 

### Nitrate/Nitrite;

• 

### TKN;

• 

### Aluminum;

• 

### Antimony;

• 

### Boron;

• 

### Cadmium;

• 

### Chromium;

• 

### Iron;

• 

### Lead;

• 

### Magnesium;

• 

### Mercury;

• 

### Mo lybdenum;

• 

### Potassium;

• 

### Selenium;

• 

### Thallium;

• 

### Ti n;

• 

### T itanium;

• 

### Va nadium;

• 

### Zinc ; and

• 

### Acet one.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 6 – Pollutants of Concern

64 

### 6.4 Selection of Regulated Pollutants

Table 6-2 lists the potential pollutant s of concern identified in Section 6.3, along with an explanation of whether EPA selected the pol lutants for regulation. Based on the documented environmental impacts from stormwater contam inated with airport deicing materials, EPA focused on regulating those pollutants exerting oxygen demand and contributing toxicity to receiving water bodies. EPA f ound that the impacts of slug loads of ADF stormwater on the dissolved oxygen of receiving streams, as well as color and odor issues associated with high ADF concentrations in stormwater discharge, are well documented. Th e main component of ADF is glycol, which exhibits significant oxyge n demand. Research by Corsi (Corsi et al., 2006) also identified potential toxicity concerns that may be linked to ADF additives, specifically triazoles and alkylphenols. ADF ma nufacturers have told EPA that the use of triazole compounds in ADF is being discontinued and that triazo le use in European ADFs has been phased out. Alkylphenols and their ethoxylates ha ve also been identified as potential toxic components of ADF. EPA’s sampling data have confirmed th e presence of these compounds; however, EPA believes that insufficient information is currently available to fully characterize the extent to which these compounds are present in deicing stormw ater and their impact. In addition, there is not currently an approved EPA method (i n 40 CFR Part 136) for these compounds.

For stormwater discharges from airfie ld deicing operations, EPA focused on the continued use of urea. Urea breaks down into a mmonia, and the resulting ammonia toxicity in receiving streams has helped to discourage urea us e as an airfield deicing chemical in the past. When inadequately treated, urea-contaminated wastewater also may contribute to nitrogen enrichment and eutrophication of receiving wate rs. Alternative airfield deicing chemicals, predominantly comprising a salt ion (potassium or sodium) and either acetate or formate, are available that are less toxic than ammonia.

Based on the known environmental impacts from deicing stormwater discharges, EPA has selected COD and ammonia (as N) for re gulation. COD is a good indicator parameter to monitor the overall oxygen demand resulting from the discharge of glycol-based ADFs and any other organic constituents presen t in the stormwater. Ammonia as N is selected for regulation to ensure that airports cease using urea as an ai rfield deicer, since othe r less toxic products are available.

EPA evaluated the impacts of the airport deicing collection and treatment scenarios on both BOD 5 

### and COD discharges. EPA selected COD for regulation and not BOD 5 

### for the following reasons:

• 

### COD a nalyses are simple to conduct and can be measured in real time compared to a 5-day test for BOD;

• 

### COD e liminates the need to consider receiving water temperature when evaluating water qualit y concerns; and

• 

### Toxic ADF additive compounds in deici ng stormwater may have a negative and variable affect on the acclimation of the active cultures used in BOD analysis, making the method less robust than COD analysis for these wastewaters.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 6 – Pollutants of Concern

65 

### Table 6-2. Potential Pollutants of Concern Selected for Regulation

Potential Pollutant of Concern Selected for Regulation Explanation of Selection or Nonselection for Final Rule
BOD 5 COD as surrogate
COD X Selected for regulation Ethylene glycol COD as surrogate Propylene glycol COD as surrogate
Benzotriazole Limited data available to support selection; potential discontinued use 5-Methyl-1H-benzotriazole Limited data available to support selection; potential discontinued use Nonylphenol, Total Limited data available to support selection; no current EPA-approved method for analysis Octylphenol, Total Limited data available to support selection; no current EPA-approved method for analysisTotal nonylphenol-3-ethoxylatenonlyphenol-18-ethoxylate Limited data available to support selection; no current EPA-approved method for analysisTotal octylphenol-2-ethoxylateoctylphenol-12-ethoxylate Limited data available to support selection; no current EPA-approved method for analysis Ammonia as nitrogen X Selected for regulation to monitor urea use
Nitrate/Nitrite Ammonia as nitr ogen as surrogate for urea use

TKN Ammonia as nitrogen as surrogate for urea use
Aluminum Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination Antimony Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination
Boron Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination
Cadmium Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination
Chromium Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination

Iron Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination
Lead Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination Magnesium Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination Mercury Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination Molybdenum Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination
Potassium Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination
Selenium Limited impact data for metals; insufficient data to support ADF as sole source of metal contaminationTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 6 – Pollutants of Concern


### Table 6-2 (Continued)

66 Potential Pollutant of Concern Selected for Regulation Explanation of Selection or Nonselection for Final Rule
Thallium Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination
Tin Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination
Titanium Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination
Zinc Limited impact data for metals; insufficient data to support ADF as sole source of metal contamination
Acetone COD as surrogate



### EPA is not regulating metals in the final ai rport deicing rule. Given the potential for background interference from airport operations, EPA does not have sufficient data to support metals as a unique pollutant from ADF alone.

6 .5 References

Corsi, S.R., et al. 2000. “Aircraft and Runway Deicers at General Mitchell Interna tional Airport, Milwaukee, Wisconsin, USA. Biochemical Oxygen Demand and Dissolved Oxygen in Receiving Streams.” (November 22). DCN AD00081.

Corsi, S.R., et al. 2003. “Nonylphenol Ethoxylates and Other additives in Aircraft Deicers, Antiicers, and Waters Re ceiving Airport Runoff.” Environmental Science & Technology , 37:4031- 4037. DCN AD00083.

Corsi, S.R., et al. 2006. “Characterization of Aircraft Deicer and An ti-icer Components and Toxicity in Airport Snow banks and Snowmelt Runoff.” Environmental Science & Technology. DCN AD00326.

ERG. 2006. Memorandum from Steve Strackbein and Cortney Itle (ERG) to Brian D’Amico and Eric Strassler (U.S. EPA). Airport Deicing Operations SWPPP and Permit Review. (November 8). DCN AD00859.

ERG. 2007a. Memorandum from Jason Huckaby (ERG) to Brian D’Amico and Eric Strassler (U.S. EPA). Airport Deicing Operations NPDES Permit Review Summary . (April 16). DCN AD00611.

ERG. 2007b. Memorandum from Maureen Kaplan (ERG) to Mary Willett (ERG). Toxic Weighting Factors (TWFs) for Nonylphenol, Octylphenol, and Alkyl Phenol Ethoxylate . (March 30). DCN AD00862.

USEPA. 2000. Preliminary Data Summary: Airport Deicing Operations. U.S. Environmental Protection Agency. Washington, D.C. EPA-821-R-00-016. (August). http://www.epa.gov/guide/airport

.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 6 – Pollutants of Concern

67 

### USEPA. 2006. Toxic Weighting Factor Development in Support of CWA 304(m) Planning Process. U.S. Environmental Protection Agenc y. Washington, D.C. (June). DCN AD00861.

USEPA. 2007. Ecotoxicology (“ECOTOX”) Database . U.S. Environmental Protection Agency. Washington, D.C. Available online at www.epa.gov/ecotox/.

USGS. 2004. Data Summary for Monitoring and Assessm ent of Changes in Water Quality Due to Deicer Management Water Years 1997-2004 . General Mitchell International Airport and U.S. Geological Survey. (September). DCN AD00085.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations

68 

### 7

. C OLLECTION AND 

### T REATMENT 

### T ECHNOLOGIES 

### A PPLICABLE TO 

### A IRPORT 

### D EICING 

### O PERATIONS


### The NPDES permit program, along with the emergence of problems such as fish kills and odor reports, have prompted airports and airlin es to investigate a wide range of pollution prevention and treatment practices. These practice s are designed to eliminate or minimize the environmental impact of ADF without compro mising safety. This section summarizes the common techniques used to coll ect deicing stormwater and th e treatment steps implemented prior to discharge. This section also discu sses pollution prevention pr actices used by U.S. airports and airlines.

Each method of collection, treatment, or pollu tion prevention selected by an airport or airline often depends on a variety of airport-specific or airline-specific factors, including climate, amount of deicing and anti-icing agents applied, number of airlines ope rating at a particular airport, aircraft fleet mix, number of aircraft operations, costs, pr esence of existing infrastructure, availability of land, and effect on aircraft departures. EPA recogni zes that some of the practices discussed in this section may not be practical or economically feasible for all U.S. airports.

EPA evaluated whether regulation of airfield deicing stormwater wa s practical or costeffective. Because airfield deicing stormwater losses tend to occur over large areas and the volumes of dilute stormwater may be very high, at this time EPA could not identify an “economically achievable” means to regulate airfield deicing stormwater other than to encourage a complete transition away from urea use. Theref ore, the technologies presented in this section are primarily used to collect and treat ADF-contaminated stormwater.

Section 7.1 discusses deicing stormwater collection, Section 7.2 describes deicing stormwater treatment, Section 7.3 discusses glycol recycling, a nd Section 7.4 presents pollution prevention (e.g., product substitution) practices.

7 .1 Deicing Stormwater Collection

The collection of deicing stormwater from ai rcraft deicing/anti-icing operations helps prevent or minimize discharges at stormwater outfalls. Airports curren tly use a variety of collection and conveyance methods, including designated aircraft deicing pads, gate and ramp area drainage collection systems, plug and pum p systems, and specially designed glycol collection vehicles (GCVs), each of which is di scussed in Section 7.1.1. I ndividual airports often rely on a combination of these collection strate gies to effectively collect ADF-contaminated
stormwater.
Section 7.1.2 presents common methods for st oring and discharging deicing stormwater, including detention ponds or cons tructed wetlands, rete ntion ponds, permanent storage tanks or frac tanks, discharge to a POTW, trucking waste o ff site, or any combination of these methods. The following sections describe in detail the various wastewater collection met hods used by the industry.

7

.1.1 Deicing Stormwater Collection and Conveyance

This section describes the various wast ewater collection and conveyance methods commonly used by airports. Airport stormwater collection systems are designed to collectTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations 

### deicing stormwater from several different locations at which de icing operations are performed, including aircraft deicing at CDPs, at the gates, or at parking or cargo aprons. Collection systems may collect stormwater from airfield deicing lo cations including ramps, taxiways, and runways. Common methods of collecting a nd conveying deicing stormwater include deicing pad collection systems, gate and ramp area drainage collect ion systems, plug and pump systems, and GCVs.

Deicing Pads

A CDP is a facility on an airfie ld built specifically for aircra ft deicing operations. It is typically a paved area adjacent to a gate area, taxiway, or runway, and constructed with a drainage system separate from the airport's main storm drain system. It is usually constructed of concrete with sealed joints to prevent the loss of sprayed ADF through the joints. The pad's collection system is typically c onnected to a stormwater storage facility, from which the spent ADF may be sent to an on-site or off-site treatment facility.

Deicing pads restrict aircraft deicing to a confined area, allowing the deicing stormwater to be captured at the point of generation and th ereby minimizing the volu me of sprayed deicing fluid discharged in an uncontrolled manner. Ai rcraft deicing pads also centralize deicing activities, which allows airports to more eas ily collect high-concentr ation ADF-contaminated stormwater. Transporting ADF-contaminated stormwat er off site to wastewater treatment plants or POTWs is also more economical when the amount of deicing stormwater is minimized.

One benefit of deicing departing aircraft on deicing pads instead of at the gates is that it frees the gates for use by arriving aircraft. Anot her benefit is that pads are commonly located near the heads of runways, where planes can be deiced just prior to ta keoff, potentially reducing the amount of Type IV anti-icing fluid necessary due to shorter holdover times and the amount of glycols transferred from the deici ng pad or released into the air. Figure 7-1 shows an example of a CDP with fixed boom sprayers.

Figure 7-1. Deicing Pad Equipped with Fixe d Deicing Booms at Pittsburgh Airport

69Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations

70 

### Gate and Ramp Area Drainage Collection Systems

Other than deicing pads, the most common areas for deicing operations are passenger terminal gates and aircraft parking or cargo ramp s/aprons. To collect wa stewater generated at these locations, some airports ha ve installed collection systems or modified existing stormwater drainage systems. The typical collection system consists of graded concrete pavement with trench or square drains that c onvey wastewater to a storage faci lity or discharge point through a diversion box. Gate and ramp collection system s generally generate low-concentration ADFcontaminated stormwater because more stormwater is mixed in with the ADF and because there are increased fugitive losses due to vehicle tr affic around the planes. For some stormwater drainage systems, a diversion box allows uncont aminated stormwater to be diverted to stormwater outfalls.

Plug and Pump Systems

Plug and pump collection systems generally comp rise devices and equipment that alter an airport’s existing storm drain sy stem to contain and collect AD F-contaminated stormwater to prevent ADF-contaminated stormwater from en tering the storm drain system. These systems include, but are not limited to, tem porary blocking devices at storm drain inle ts and/or shutoff valves in the storm sewer system. Some airports use storm drain inserts or plugs to close the drains and allow the ADF-contaminated stormwat er to collect within the existing airport stormwater drainage system. Wh en aircraft are undergoing deic ing/anti-icing, the inserts are installed to force contaminated stormwater to poo l in drainage piping until it can be vacuumed or pumped out. This practice pr events manholes and stormwater piping from overflowing. Once deicing/anti-icing activity ends and the contamin ated stormwater is re moved, the storm drain inserts can be removed, or deactivated allowi ng uncontaminated stormwat er to pass through the drain. Plug and pump collection syst ems are applicable to airports that deice at the gate and may be utilized to convert ramp areas (e.g., cargo, feeder, taxiways) into deicing areas. One benefit of deicing at the gate is that the components of the existing collec tion system infrastructure (i.e., existing storm sewers) can be incorporated into the plug and pump colle ction system, reducing the costs associated with deicing control.

Minneapolis/St. Paul International (MSP) airp ort is one example of an airport using a plug and pump collection system. At MSP airport, 30 percent of deicing operations takes place in the airport’s 16 plug and pump containment ar eas. During the deicing season, the plug and pump areas are fitted with compression plugs in the storm sewers to prevent contaminated or potentially contaminated stormwater from bei ng discharged. The stormw ater plugs convert the stormwater sewer pipes and manholes into individual stormwater re tention systems that can each retain between 5,000 to 42,000 gallons of stormwater. These indivi dual stormwater retention systems are monitored during the da y to determine how full they ar e (to prevent overflow) and to determine how to manage the ADF-contaminat ed stormwater based on its composition and strength. Contaminated stormwater is pumped or vacuumed from the sewer pipes and tested to determine the glycol concentra tion. Based on the glycol concentr ation of the wastewater, it is stored in either a low-concentration storage ta nk or a high-concentrati on storage tank prior to being shipped off site (USEPA, 2008a).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations 

### GCVs

GCVs are specially designed vehicles that re move stormwater contaminated with deicing materials from airport deicing pads and gate locations by vacuuming liquid from pavement surfaces. GCVs help prevent ADF losses through ev aporation and/or direct discharge and allow ADF-contaminated stormwater to be collected for treatment or disposal. Drain covers that bond to surfaces to quickly seal off drains are often used in conjunction with GCVs in the area where aircraft are deiced to allow the GCVs to collect high-concentration spent deicing fluid.

Commercial GCVs have two ba sic designs: truck chassis or trailer mounted. The truck chassis designs are adapted from the street sweeper concept, with a vacuum unit, vacuum/sweeper head, and storage tank all m ounted on a single self-propelled vehicle. Typically, a separate engine powers the vac uum system. Trailer-mounted designs have the vacuum unit, collection head, and storage tank on a towed platform with power provided by either an engine mounted on the trailer chassis or a power take-off from the tow vehicle, typically a tractor. Figure 7-2 shows an example of a GCV. GCVs help prevent ADFcontaminated stormwater from reaching unpaved areas where infiltration could occur and from contaminating surrounding waterways.

Once ADF-contaminated wastewater is vacuumed from airport surfaces, it is typically transported to an on-site storage facility (either temporary or permanent) where the airport can then treat and discharge or ship the waste off s ite. In addition, some airports with collection and conveyance or plug and pump systems will have a designated area where the GCV can discharge into the collection system, allowi ng the existing infrastructure to convey the material to final storage.

Figure 7-2. GCV

71Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations

72 

### Plug and Pump with GCV

Commonly, a plug and pump system is operated in conjunction with GCVs or a tanker truck with pumps that collect the deicing stor mwater that builds up be hind the drainage block during the deicing event. Additiona lly, GCVs may be used outside of the blocked area to collect ADF-contaminated stormwater to enhance what can be collected through the plugging operation alone.

7.1 .2 Deicing Stormwater Storage

This section describes the various stormwater storag e methods commonly used by airports. Airport stormwater storage systems ar e designed to retain de icing stormwater from several different locations around an airport, accommodate highl y variable flows and volumes, and may retain/store stormwater th at contains pollutants from both airfield and aircraft deicers. Common methods of stormw ater storage at airports include detention ponds, equalization ponds, retentions ponds, and storage or frac tanks.

Detention Ponds/Lagoons and Equalization Ponds

Detention ponds/lagoons are open-water ponds th at collect deicing stormwater from runways and other airport prope rty. Detention ponds and lagoons are designed to temporarily hold deicing stormwater anywhere from one day to two months and allow solids to settle while reducing oxygen demand through surface oxygenation and volatilization prio r to discharge to receiving waters. Detention ponds and lagoons can be lined or gravel-filled and may contain microscopic bacteria that biode grade deicing and anti-icing ma terials. Pump stations are commonly implemented to pump metered wastew ater to discharge or further treatment. Detention basins often use aeration to incr ease dissolved oxygen levels. Lagoons may be equipped with a floating cover.

Equalization ponds are detention ponds desi gned to thoroughly mix ADF-contaminated stormwater so that consistent concentrations of pollutants can be pumped from the pond to treatment operations or to other disposal. Equa lization ponds may contain moving parts, such as mixers, to ensure the liquid in the pond is completely mixed.

Retention Ponds

Retention ponds are designed to hold collected deicing stormwater indefinitely. Usually the pond is designed to allow ove rflow to drain to another lo cation (e.g., a second retention pond or other overflow structure) when the water level gets above the pond capacity. Retention ponds can also be used to treat deici ng stormwater as part of a batc h process (using chemical addition and/or aeration) prior to discharge. With retention ponds, airpor ts can collect ADF-contaminated stormwater throughout a deicing s eason and have the option of truc king it off site for treatment or treating it on site in the retention pond.

Advantages and Disadvantages of Po nds in Treating ADF-Contaminated Stormwater

Ponds require large areas for installati on and their wastewater normally requires treatment for many months after th e end of the annual deicing season before it can be discharged.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations 

### FAA discourages airports from installing new stor mwater retention ponds, as they can be a lure for birds, which are a safety hazard for aircraft (FAA, 2007). For airports with existing retention ponds and adequate storage capacity, aerated po nd systems may be able to provide efficient treatment. See section 7.2.1 for furthe r discussion of aerated pond systems. Figure 7-3 shows an example of an airport pond used for deicing stormwater storage.

Figure 7-3. Pond for Deicing Stormwater Storage

Storage Tanks

Airports that treat ADF-contaminated stormwat er often use tanks to store the stormwater prior to on-site treatment or transfer off site . These types of tanks can be constructed as aboveground tanks or underground tanks. Collecting and storing deicing st ormwater in storage tanks allows an airport to equalize pollutant concentrations and flow the stormwater at a consistent flow rate into an on- site treatment system, which is important to ensuring consistent treatment results. Portable storage tanks, called frac tanks, can be placed on the airport property (while empty) and provide temporary storage of collected deicing stormwater. These types of tanks may also be connected by a hose or pipeline to an alternative area. Figure 7-4 shows an example of two frac tanks.

73Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations



### Figure 7-4. Frac Tanks

7.2 Treatment

This section describes the various means of treating stormwater contaminated with deicing chemicals. The technologie s described within this section are typically used to control ADF-related pollutants; however, st ormwater with pollutants from airfield deicing operations may also be routed into these systems.

7

.2.1 Biological Treatment

This section describes the treatment of ADF- contaminated stormwater through biological processes. Biological treatment consists of two ty pes of processes, aerobic or anaerobic, and can take place on site at an airport or off site at POTWs or other tr eatment facilities.

POTW Treatment of ADF-Contaminated Stormwater

Where practical, airports discharge their deic ing stormwater to a POTW for biological treatment. POTW systems generally use activat ed sludge in an aerobic biological treatment system and may also incorporate anaerobic di gestion of the sludge generated. In aerobic treatment systems, microorganisms consume the or ganic matter and convert it to water, carbon dioxide, and additional biomass in the presen ce of oxygen. To maintain the microorganism population in the treatment process, POTWs usi ng an activated sludge process will use an aerated treatment tank followed by a sludge settling tank. Part of the settle d sludge is recycled back into the aerated treatment tank and the re mainder is removed for further processing or disposal.

Airports may be prevented from dischargi ng ADF-contaminated stormwater to a local POTW for one or more or the following reasons: (1 ) limited hydraulic or loading capacity at the POTW, (2) high POTW wastewater treatment and/or conveyance fees, (3) inability of the local POTW to handle highly va riable pollutant loadings, and/or (4 ) airport infrastructure constraints.

74Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations

75 

### Aerated Ponds

Aerated ponds used on site at airports are effective for treating low-concentration ADFcontaminated stormwater. These are ponds that are open to the atmo sphere, though open-topped tank systems may also be used. Aerated ponds are not generally used for high-concentration ADF-contaminated stormwater because the pond s do not have sufficient oxygen transfer to completely convert the ADF pollutants into wate r, carbon dioxide, and biomass compared to an activated sludge system. Treatment ponds may range in size and are usually operated as a batch
process.
Aeration in lagoons and ponds increases the level of dissolved oxygen in the water, which is needed to decompose organic matter such as glycols. In addition, oxygen helps to oxidize certain elements that are suspended in th e water, and oxidation causes some materials to become heavier so that they w ill settle out of the water column quicker. Without proper aeration, bacteria cannot decompose the organic matter in a pond quickly or efficiently. Aeration devices are used to agitate the lagoon or pond surface, which helps to transfer atmospheric oxygen into the wastewater to promote biol ogical treatment processes, vent carbon dioxide and other gaseous elements from the water, and increase the amount of wastewater exposed to ambient air, allowing other volatile organics to oxygenate and evaporate.

The Greater Rockford airport is an exam ple of an airport operating an aerated pond treatment system for deicing stormwater. Great er Rockford airport collects ADF-contaminated stormwater throughout the deicing season into a 16-million-gallon aerated detention pond. Its aerobic digestion system consists of the aerat ed detention pond, a settling pond, a re-circulating pump, and a chemical addition bu ilding. The biodegradation of glyc ol is temperature-dependant and predominantly occurs during the spring and early summer months when ambient temperatures are higher. Airport personnel monito r the process, adding nutrients, antifoaming agents, and pH adjustment chemicals as needed. When the BOD 5 

### concentration of the pond has been reduced to less than 30 mg/L, airport personnel discharge the treated stormwater from the settling pond to Rock River (USEPA, 1999).

Figure 7-5 shows an aerated pond installati on at Portland Airport (Oregon).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations



### Figure 7-5. Aerated Pond Installation at Portland Airport

Anaerobic Treatment

Anaerobic treatment systems can effectively treat ADF-contaminated stormwater with a range of glycol concentrations. Th is type of treatment usually o ccurs in a closed tank in which microscopic bacteria in an oxygen-deficient environment biode grade deicing and anti-icing materials. In anaerobic treatment systems, microorganisms consume the organic matter and convert it to methane and carbon dioxide in th e absence of oxygen, which creates much less sludge than an aerobic system.

AFB treatment is a demonstrated te chnology for addressing ADF-contaminated stormwater at both the Albany, New York (A LB) and Akron/Canton, Ohio (CAK) airports. Additionally, Portland comp leted construction of an AFB in 2011 and testing is slated to be complete in 2012. TF Green Airpor t (Providence, RI) is designi ng an AFB system, estimated to be operational in 2015. (Rhode Island Airport Co rporation, 2011). The AFB treatment system uses a vertical, cylindrical tank in which the ADF- contaminated stormwater is pumped upwards through a bed of granular activated carbon at a ve locity sufficient to fluidize, or suspend, the media. A thin film of microorganisms grows and coats each granular ac tivated carbon particle, providing a vast surface area fo r biological growth. The anaerobi c microorganisms that develop occur naturally in sediment, peat bogs, cattle intestines, and even brewer's yeast. Breakdown products from the AFB treatment system incl ude methane, carbon dioxide and new biomass. Effluent from the AFB can be discharged to a lo cal POTW or, in most cases, directly to surface
water. Figure 7-6 presents a diagram showing the major components of a typical AFB treatment system (Source: US Department of Defense, 2003).

Treating wastes using an anaerobic biological system compared to an aerobic system offers several advantages. Because it does not require aeration, the anae robic system requires

76Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations 

### less energy and produces less than 10 percent of the sludge of an aerobic process. In addition, because the biological process is contained in a sealed reactor, odor s are eliminated. EPA evaluated AFB biological treatme nt as it represents the best technology currently in use by airports to treat deicing stormwat er prior to dir ect discharge.

Figure 7-6. Typical Anaerobic Fluid Bed T reatment System for Treatment of ADFContaminated Stormwater

Land Application and Constructed Wetlands

Low-concentration deicing stormwater may also be treated on site at an airport using either land application or disc harge through constructed wetlan ds. Land application involves spraying deicing stormwater onto a land surface for infiltration and biological degradation within the soil. As an example, Salt Lake City Intern ational (SLC) airport us es land application to dispose of batch volumes of low-concentration deicing stormwater on a periodic basis. The system sprays approximately 300,000 to 400,000 gall ons of stormwater over nutrient-enriched land using agricultural wheels. The application is sprayed at a rate of a bout 1 gallon per square foot over a two-day period. The sprayed glycol th en degrades in the soil over a week to monthlong period (USEPA, 2008b). Because glycol-based ADFs readily degrade in both high clay and sandy soil systems, this type of system can be effective for low con centrations and limited volumes. Biodegradation occurs in the soil thro ugh carbon respiration of soil microbes, which consume oxygen and release carbon dioxide. Zurich International Airport, Switzerland, also uses a spray irrigation system for ADF treatment. At th at airport, a heated sprinkler system applies ADF-contaminated stormwater to a 20 ha ( 49.4 acre) area (Jungo E ngineering Ltd, 2005).

Constructed wetlands are artificial marsh es or swamp s placed inline with stormwater drainage at airports . The wetlands act as biofilters and help remove sediments and pollutants such as heavy metals from the wastewater. Physical, chemical, and biological processes combine in wetlands to remove contaminants from th e wastewater. The discharge from constructed wetlands can also be collected and treated if it cannot meet discharge permit limits or it can be discharged to a POTW or surface water.

77Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations

78 

### 7

.2.2 Physical Separation

This section describes physical separati on processes that are used to treat ADFcontaminated stormwater. Physical separation cons ists of four types of processes: filtration, MVR, membrane separation, and dis tillation. The treatment can take pl ace on site at an airport or off site at other treatment facilities.

Filtration

Primary filtration, which removes solids grea ter than 10 microns, is commonly the first step in glycol treatment systems because it re moves suspended solids and prevents subsequent processing units from plugging. This technology is typically used in combination with other technologies. Popular primary filters used in gl ycol treatment are made of either polypropylene cartridges or bag filters.

MVR

MVR is an evaporation method that uses mech anically driven compressors or blowers to increase the pressure of the vapor produced. The increase in pressure causes the vapor’s temperature to increase, which allows it to heat the liquid being concentrated. Benefits of using MVR in glycol treatment include:

• 

### Low specific operating costs;

• 

### Low specific energy consumption;

• 

### Short residence times of the product; and

• 

### Simplicity of the process.

EPA conducted a site visit and subsequent sampling episode at Denver International (DEN) airport, which operates MVRs in the fo llowing manner. MVRs c oncentrate the deicing pad storage tank influent, which ranges from 1 to 12 percent PG, to a final concentration of 50 to 55 percent glycol. Each MVR has a capacity of 3,250 gallons per day. The effluent from the MVRs goes to a storage tank where it is stockpile d prior to being sent to a distillation system (USEPA, 2007b). The evaporative process may also generate a condensate, which in most cases requires further treatment prior to indirect discharge. Typicall y, this is managed via an RO system, with the concentrated material returned to the treatment process and the RO permeate discharged to a POTW.

Membrane Separation

Membrane separation is an efficient one- or two-step process that incorporates ultrafiltration (UF) and/or RO to increase the ADF concentrations of ADF-contaminated stormwater. In an UF/RO process, fluid is filt ered at a high temperat ure (75o C) using an ultrafiltration membrane as stage one. Next, th e deicing fluid (ultrafiltration filtrate) can be dewatered using an RO membrane as stage tw o. The UF membrane is effective at removing contaminants such as turbidity, color, and odor , and RO stage two is used for dewatering and glycol separation. The combined UF/RO proces s produces a final glyc ol concentration of approximately 10 percent from an original co ncentration ranging betw een 0.5 and 4 percent. Pittsburgh International (PIT) airport uses this type of system. The PIT system first treats ADFcontaminated stormwater through an UF unit to remove suspended solids. At this point, theTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations

79 

### stormwater is 0.5 to 4 percent PG. The stormwater is next treated through an RO unit. Following RO, the stormwater is split into two outputs: 1) concentrate that is approximately 10 percent PG, and 2) permeate that has a very low glycol concentration. The con centrated PG is transported off site for further processing and the permeate containing small amounts of glycol, CBOD, and COD is sent to the POTW for further processing (USEPA, 2006).

Distillation

Distillation can effectively treat ADF-contam inated stormwater by separating the water from the glycol. A potential drawback of distillati on is that it creates a distillate that requires further treatment. Depending on whether the di stillation system is operated in a batch or continuous mode, the majority of the distillate can be discharg ed to the local POTW without further processing. In a batch mode , there is a “mid-cut” water/gl ycol mixture, which marks the transition from water removal and product; this volume is redirected to the process feed. However, depending on system design and applicable li mits, distillate may be able to be directly discharged. Distillation columns ma y be larger and more expensiv e than other technologies to operate, and because distillation is energy-intensiv e, it is generally not cost-effective to distill waste glycol solutions at low c oncentrations (less than15 percen t). Design variables for this technology include temperature, di stillation column height, and reflux ratio. This process is commonly done in batches to ensure prope r distillation and de sired results.

EPA conducted site visits at SLC and DEN ai rports, both of which operate distillation columns.

• 

### At DEN airport, the distillation system runs 24 hours a day for a three-week cycle and processes about 225,000 gallons of PG before the system is halted for cleaning and maintenance. The distilla te from the distillation column is discharged to the airport’s storage ponds. The distillati on column bottoms compile sludge that is classified as sp ecialized nonhazardous waste. The 98 to 99 percent PG from the disti llation column is pumped to a polisher (USEPA, 2007b).

• 

### At SLC airport, 40 to 45 percent glyc ol-concentrated stormwater is passed through a finisher (one stage of evaporat ion) to increase the concentration to approximately 70 to 80 percent glycol and then discharged to a storage tank. The stored concentrate is sent to a distillati on column where it is heated to 250 to 260 degrees Fahrenheit to produce a final pr oduct of 100 percent gl ycol. Distillate from the distillation column is discharged to a storage tank prior to RO treatment and indirect discharge. The column bottoms (residual solids) are disposed of at an off-site facility landfill (USEPA, 2008b).

7 .3 Recycling

Recycling glycol from ADF-contaminated stormwat er decreases the amount of ADFcontaminated stormwater that reaches and pot entially impairs surface and ground waters. The process to recover glycol from ADF-contaminated stormwater may take several steps and can be conducted both on site at the airpor t and/or off site at a regional treatment facility. The recycle and recovery technologies currently in use by U. S. airports include filtration, MVR, membrane separation, and distillation (discuss ed in Section 7.2). On-site recycling typically includes some combination of these technologies, configured as an integrated tr eatment train to meet specificTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations

80 

### requirements of the airport where it is located. Most commonly, an on-site facility initiates the process to increase the glycol concentration to make transport to a regional facility for final processing more cost-effective.

Recovered glycol is generall y sold to help recover expe nses associated with ADF application, collection, and contro l. On-site recycling was successful and economically viable at the airports visited by EPA that collected large enough volumes of high-concentration ADFcontaminated stormwater. However, recovery systems may also be able to handle lower concentration ADF stormwaters (with glycol concen trations in the 1-2 percent range), and smalland medium-hub airports may be able to re cover and recycle glyc ol using off-site recycle/recovery facilities. Off-site facilities can recycle ADF-contaminated stormwater from airports not generating sufficien t volumes to warrant on-site recycling and treatment. Glycol recycling vendors offer a variety of recycle/recovery related services to accommodate different airport sizes and configurati ons. Services commonly provide d by glycol recycle/recovery vendors include supplying drain bloc ks, leasing portable storage ta nks, on-call trucking services, and tote (fluid container) pickups . Key criteria for determining th e appropriate r ecycle/recovery program include the type of ADF being collected, glycol concentration of the stormwater, total consumption of ADF per season, and peak ADF volume application rate s. Other factors to consider are the number of deicing days per seas on at an airport and fu ture air traffic plans.

7 .4 Pollution Prevention and Pr oduct Substitution Practices

Pollution prevention practices reduce the generation or discharge of pollutants produced during aircraft/airfield deici ng operations. Pollution preven tion practices implemented throughout the aviation industry include infrared deicing, forced-air deicing, product substitution practices, and BMPs.

Infrared Deicing

Infrared heating involves transmitting en ergy using electromagnetic waves or rays. Infrared energy is invisible and travels at the speed of light in straight lines from the heat source (the emitter) to all surfaces and objects (the receivers) without significantly heating the space (air) through which it passes. This heating process is much fast er than convection or conduction heating mechanisms used by conventional deicin g, where the deicing fluid spray is cooled by ambient air.

Figure 7-7 shows a picture of the infrared hanga r at John F. Kennedy (JFK) airport.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations



### Figure 7-7. Infrared Hangar at JFK

Infrared-based aircraft deicing systems offer two advantages over trad itional glycol-based deicing methods. From an environmental standp oint, they can greatly reduce the amount of glycol-based fluids used for aircraft deici ng, while from an operational standpoint, they are relatively inexpensive to operate, as they use natural gas or propane as fuel.

Any infrared deicing facility must take in to account the physical ch aracteristics of all aircraft that will use the system. For example, an infrared system design factors in the maximum tail height, the shape of tails, maximum wingspans , and differences in the length and width of the fuselage. The site selected for an infrared de icing system must comply with the same FAA regulations that apply to glycol -based aircraft deicing faciliti es, including aircraft separation rules, airport traffic control tower line-of-sight criteria, and requirements to not interfere with radar signals, navigational aids , and airport lighting. FAA issued a new Advisory Circular in 2005 specifically for infrared deic ing facilities (FAA, 2005). As with traditional aircraft deicing facilities, an infrared deicing facility must provide taxiways that allow aircraft to bypass the deicing facility.

While EPA encourages the use of this tec hnology, industry practi ce has shown that it may not be applicable at all airports and it appear s to be best used in conjunction with other more conventional deicing operations (ERG, 2004; Belcher-Hoppe Associates, Inc., 2004).

Forced Air Deicing

Forced air deicing uses large volumes of air at low pressure to remove loose accumulations of snow and ice from an aircraft prio r to chemical deicing. Aircraft deicing trucks or fixed booms equipped with forced air nozzles help reduce the am ount of glycol that is used during deicing and defrosting operations. In light snow conditions, forced air may completely replace the need for deicing flui d. For light frost and light deici ng events, fluid-injected forced air can be used to reduce the amount of deic ing fluid by up to 75 per cent. For heavy deicing events, a fluid forced air technique is used. Th is technique requires the ADF application rate

81Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations

82 

### sprayed from the boom to be reduced from 60 ga llons per minute (gpm) to 40 gpm to achieve a 25-percent reduction in deicing fluid per aircraft. Forced ai r deicing can reduce operational expenses, environmental impacts, and subseque nt environmental monitoring or remediation expenses (Icewolf product flyer; IDS, 2006).

Aircraft Deicing/Anti-Icing Pr oduct Substitution Practices

One solution to the environmental problems associated with glycol-based ADF is replacing such fluids with more environmentally friendly products. ADFs need to meet FAA’s Aerospace Material Specification (AMS) 1424 for Type I fluids and AMS 1428 standards for Type IV fluids. These standards require a specified level of product performance and compatibility and any alternative product must meet the same standard s. To be economically viable, alternative products must also be compar ably priced and be at least as effective in maintaining air safety as the glycol-based fluids they replace and less harmful to the environment.

EPA is aware of one non-glycol, plant-de rived product currently being marketed by Cryotech Deicing Technology. A new Type I ADF product called “DF Sustain” uses 1,3- propanediol rather than PG, and is manufactured by a fermentation process using cornstarch. The manufacturer claims performance equal or better than PG- or EG-based deicers.

Table 7-1 lists other aircraft deicing alternatives that EPA is aware of based on literature reviews, industry meetings, and site visits . In addition, the airpor t and airline industry associations as well as U.S. Air Force have conducted and are continuing to conduct research into other potential substitutes for PG- and EG-based fluids.

Table 7-1. ADF Alternatives

Alternative Comments
PG ADF usage data indicates a trend towards greater PG use as an alternative to EG

use. Hot Air, Forced Air, and Tempered Steam Deicing The use of hot air, forced air, or temp ered steam when deicing aircraft is an alternative to typical deicing fluid application techniques using deicing trucks with conventional spray nozzles alone. These alternatives can provide more effective deicing than conventional spraying techno logies and result in lower ADF usage. Infrared Deicing Infrared deicing is an alternativ e to conventional ADF usage and can greatly reduce (though not eliminate) the use of ADFs for deicing and anti-icing. Cryotech Bio-PDOTM This bio-based product is cu rrently being marketed as an alternative to conventional PG-based Type I fluids. Warm Fuel for Wing Deicing This type of deicing is an alternative to defrost deicing with ADF.



### Airfield Deicing Produc t Substitution Practices

Environmental problems associat ed with past airfield deicin g products like urea led to the development of the alternative airfield deicing chemicals us ed today. Potassium acetate has replaced urea as the primary airfield deicer at many U.S. airports. The U.S. Armed Forces no longer purchases airfield deicers that contain urea and instead use pot assium acetate, sodium acetate, and sodium formate. These airfield deic ers are highly effective at low temperatures, exert much lower oxygen demand than urea, and offer less environmental impact.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations

83 

### The aviation industry is curre ntly evaluating the impact of common airfield deicing chemicals on the environment, runway infrastruc ture, and chemical corro sion of aircraft carbon brakes. Based on the results of this work, EPA anticipates that altern ative airfield deicing chemicals will be identified and ultimately incorpor ated into practice. EPA is aware of one such product, Cryotech’s Bio-PDOTM 2 

### , which is currently being used as an additive for potassium acetate runway deicers. The Cyrotech BX36 runw ay product performs similarly to its widelyused E36 product, but with reductions in electri cal conductivity and potassium content (reducing carbon brake issues), and a bio-based material composition of 75 percent, allowing for easy degradation.

BMPs

BMPs are techniques used to limit the amount of ADF applied or allowed to mingle with stormwater. EPA defines a BMP as a "technique, meas ure or structural contro l that is used for a given set of conditions to manage the quantity and improve the quality of stormwater in the most cost-effective manner." This sec tion describes the following airc raft/airfield deicing-related BMPs:

• 

### A pplication rates and deicing fluid dilution;

• 

### A irfield prewetting;

• 

### I ce detection systems;

• 

### E nhanced weather forecasting;

• 

### H eated sand;

• 

### Se paration of contaminated snow;

• 

### A nnual employee training;

• 

### Me chanical deicing and snow removal;

• 

### Ye arly inspections of deicing e quipment and infrastructure; and

• 

### Ty pe IV anti-icing.

Application Rates and Deicing Fluid Dilution

Deicing personnel can minimize the amount of de icing fluid used at an airport by varying deicing fluid application rates and the ADF d ilution mix to best match each deicing event condition. Application rates are commonly evaluated every time de icing is required. However, ADF is usually premixed to a set 55 percent or 45 percent glycol con centration. Systems that allow for ADF dilution adjustment based on the weather conditions can use less. Ice thickness, ambient temperatures, and plane size all dete rmine application rate s and fluid dilution requirements. Small planes with small amounts of frost can require as little as 50 gallons of ADF while large planes with thic k ice accumulations can take up to 2,000 gallons to deice. Application rates controlled by ch emical metering systems instal led to deicing trucks or booms allow the applicator to control the distribution of chemicals and maintain a consistent application rate at all times. Using a chemical metering sy stem also allows the operator to change the application rate in mid-applicati on based on changing weather conditions.

2 Mention of Cryotech products should not be construed as an endorsement from EPA.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations

84 

### Airfield Prewetting

Airfield prewetting involves applying a dry chemical followed by a light coating of liquid deicer to airfield pavement. During icy conditi ons, a granular deicer is generally used to penetrate ice and increase surface area prior to us ing a liquid deicer (generally PG) to help the solid deicer stick to the pavement and prevent dr y pellets from blowing off. Responses to EPA’s airport questionnaire indicated that prewetting is common and helps lower the cost of materials by increasing the rate at which the liquid deic er contacts icy surfaces and by minimizing wind losses of solid deicer. Following prewetting, snow and ice are generally removed from airfield areas using mechanical equipmen t (such as plows and brooms).

Ice Detection Systems

Ice detection systems include sensors installe d on runways and taxiways that transmit constant surface and subsurface temperature readi ngs to deicing control personnel. These sensors indicate whether there is a potenti al for ice to form on the paved surfaces. Airports can then use the information provided by individual deicer manufacturers to determine whether to apply deicing/anti-icing chemicals.

Enhanced Weather Forecasting

Many of the larger U.S. airports use enha nced weather forecasting systems to help determine when they will require deicing activ ities. A popular weather forecasting product on the market is the Weather Support to Deicing Deci sion Making (WSDDM) software program. This system is a “nowcasting” system that is used to confirm National Weather Service data and forecasts. WSDDM provides forecasts, monito rs storms and provides real-time storm information, and estimates and detects prec ipitation. WSDDM can provide the following services to the user:

1. R eal-time snow gauge data (updated ever y minute) of the liquid equivalent snowfall rate at the airport and two to three sites 10 to 20 kilometers (km) away from the airport;

2. R eal-time radar reflectivity from rada rs depicting current locations of precipitation and snow;

3. Meteorological data at the airport and tw o to three sites 10 to 20 km away from the airport updated every mi nute and displayed in text and time line form, with the time line going back two hours;

4. T hirty-minute nowcast of radar reflectivity based on a cross-correlation technique on the radar reflectivity data updated every six minutes; and

5

. Thirty-minute nowcast of liquid equivalent snowfall rate at the airport and the offsite snow gauge locations by applying a real-time snow gauge-radar reflectivity calibration algorithm at each of the snow gauge sites, updated every six minutes.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations

85 

### WSDDM can improve pollution prevention by pinpointing when deicing operations are actually needed, which lowers the amount of ADFs used to keep departing aircraft free of ice and snow at takeoff and lowers the amount of anti-ici ng chemicals used to prevent ice and snow from bonding to aircraft and taxiways (ERG, 2005).

Heated Sand

Sand trucks can be parked in a heated garage with heat piped to the truck. Heating sand trucks accomplishes two things. First, heating th e truck prevents the moisture in the sand from freezing and clumping, which would prevent the sa nd from being efficiently disbursed when applied. Second, applying heated sand to icy su rfaces can melt ice and the sand provides needed traction when the surfaces refreeze, which mini mize the need to use pavement deicers.

Separation of Co ntaminated Snow

Airports often segregate glycol-contaminated snow (commonly called “pink snow”) and haul it to a designated area where the snow me lt can be collected. Deicing pads often contain designated areas to store contaminated snow so th at the snow melt can be commingled with other deicing stormwater.

Annual Employee Training

Training and experience of pe rsonel performing aircraft de icing/anti-icing operations affects the efficiency of aircraft deicing/anti -icing. Well-trained and e xperienced deicing/antiicing personnel improve the efficiency of aircra ft deicing/anti-icing operations and minimize the volume of ADF used. The training and experience of airport personnel may also affect the efficiency of airfield deicing operations. Airport personnel are t ypically responsible for clearing taxiways, gate areas, ramps, aprons, and deicing pads. When these areas are not adequately cleared, snow and ice accumulate on the underc arriage and the undersid e of aircraft during taxing and must be removed prior to takeoff.

Many airports conduct annual operations and maintenance training, with specialized winter operations training usually conducted prior to th e deicing season. This specialized training can include but is not limited to proper use of e quipment, application of chemicals, and location of snow melt areas. Staff ma y also be trained in environm ental awareness detailing the requirements of airport permits and BMPs associat ed with airport deicin g/anti-icing operations.

Mechanical Deicing and Snow Removal

The amount of ADF required to deice aircraft can be minimized by mechanically deicing the aircraft prior to chemical deicing. Mechani cal deicing is generally economical only for small aircraft because mechanical deicing of large ai rcraft is labor-intensive and time consuming. A drawback of mechanical deicing is that aircraft (e.g., aircraft antennae and sensors) risk being damaged by incorrect mechanical deicing methods . Despite the risk of aircraft damage, many airlines use brooms, squeegees, and ropes, amon g other items, to remove ice and snow from aircraft surfaces. These methods are more eff ective at removing snow rather than ice.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations

86 

### Snow is commonly mechanically removed on airfield pavement, including passenger ramps, gate positions, taxiways, and runways, prior to ADF being applied, to prevent contamination of the snow. The following types of equipment are used to remove snow from airfield surfaces: self-propelled snow brooms, high speed snow blowers and snow plows, and utility trucks or tractors fitted with snow brooms or plows. Phys ical means are generally used to remove snow rather than ice.

Yearly Inspections of Deicing Equipment and Infrastructure

Inspections are conducted to ensure that e quipment used for deicing operations is working properly and to determine where ma intenance may be needed. Storage tanks are inspected to ensure there are no leaks. ADF app lication equipment is inspected to determine if gauges are working properly and th at fluid is not being spilled. Trench or square drains are inspected to ensure there is no clogging and that water conve yed through the drain does not escape. Other equipment and airport infrastructu re may require yearly inspections to make certain that deicing chemicals are applied wi th properly functioning equipment and collected with suitable infrastructure.

Type IV ADF Anti-icing

Type IV ADF protects aircraft from ice, s now, or slush accumulations on cleaned aircraft surfaces. Type IV fluids form a protective fi lm on treated surfaces, protecting against ice formation and/or snow accumulation. Pretreating aircraft with Type IV fluid is sometimes used when ice is in the forecast and an aircraft is expected to remain on the ground for an extended period of time. This type of an ti-icing treatment can reduce the amount of deicing fluid needed for an aircraft by reducing the amount of ice that forms on the aircraft.

7 .5 References

Becher-Hoppe Associates, Inc. 2004. Airport Facilities - Rhinel ander - Oneida County Airport

. (December 6). DCN AD00097.

CASQA. 2003. Vegetated Swale . (January 1). California Stormw ater Quality Association, Menlo Park, CA. DCN AD01137.

ERG. 2004. Aircraft Deicing using an Infr ared System called Ice-Cat. (December 13). DCN AD00095.

ERG. 2005. Memorandum from Steve Strackbein (ERG) to Project File: Summary of Weather Support to Deicing Decision Ma king (WSDDM). A Winter Weather Nowcasting System. (January 3). DCN AD00185.

ERG. 2007. Memorandum from Juliana Stroup and Mary Willett (ERG) to Brian D’Amico (U.S. EPA). Aircraft Deicing Stormwater Control Tec hnologies and Their Removal Efficiencies

. (December 17). DCN AD00855.

FAA. 2005. Federal Aviation Administration Advi sory Circular 120-89. “Ground De-Icing using Infrared Energy. (December 13). DCN AD01139.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 7 – Collection and Treatment Technologi es Applicable to Airp ort Deicing Operations

87 

### FAA. 2007. Federal Aviation Administration A dvisory Circular No. 150/5200-33B. “Hazardous Wildlife Attractants on or Near Airports.” (August 28). DCN AD01138.

Icewolf. The Evolution of Aircraft De icing Systems, Icewolf, Product Flyer. DCN AD00096.

IDS. 2006. Deicing the IDS Way , Product Flyer. (Ja nuary 4). DCN D00077.

Jungo Engineering Ltd. 2005. Disposal of De-icing Effluent by Irrigation. (June 6-8). DCN AD01200.

Rhode Island Airport Corporation. 2011. RIDEM and RIAC Reach Agreement . (December 21). www.dem.ri.gov/programs/benvir on/water/permits/ripdes/pdfs/riacprelim.pdf. DCN AD01286.

US Department of Defense. 2003. ESTCP, Mineraliz ation of TNT, RDX, and By-Products in an Anaerobic Granular Activated Carbon Flui dized Bed Reactor, (April). DCN AD00898.

USEPA. 1999. Final Engineering Site Visit Report for Greater Rockford International Airport. U.S. Environmental Protection Ag ency. Washington, D.C. DCN T10402.

USEPA. 2006. Final Engineering Site Vi sit Report for Pittsbur gh International Airport. U.S. Environmental Protection Agency. Washi ngton, D.C. (November 1). DCN AD00774.

USEPA. 2007a. Final Engineering Site Visit Report for Seattle - Tacoma International Airport. U.S. Environmental Protection Agency. Washington, D.C. (July 1). DCN AD00778.

USEPA. 2007b. Final Engineering Site Visit Report for Denver International Airport . U.S. Environmental Protection Agency. Washi ngton, D.C. (November 4). DCN AD00779.

USEPA. 2008a. Final Engineering Site Visit Report fo r Minneapolis-St. Paul International Airport. U.S. Environmental Protection Agenc y. Washington, D.C. (January 24). DCN AD00793.

USEPA. 2008b. Final Engineering Site Visit Report fo r Salt Lake City Inte rnational Airport

. U.S. Environmental Protection Agency. Wa shington, D.C. (Janua ry 24). DCN AD00792.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 8 – Performance of Control and Treatment Scenarios

88 

### 8

. P ERFORMANCE OF 

### C ONTROL AND 

### T REATMENT 

### S CENARIOS


### EPA evaluated the performance of the select ed control and treatm ent scenarios based on their ability to collect and tr eat ADF-contaminated stormwater and/or their ability to reduce pollutant loadings. EPA used airport-specific esti mates of Type I and IV ADF to calculate the volumes of applied and available ADF at each of these airports (ERG, 2011a). EPA then evaluated the collection ranges of both the data collected by EPA and the data available in the Transportation Research Board (TRB) manual (TRB Airport Cooperative Research Program, 2009), combined with best engineering judgment to estimate the collection efficiency of each of the technologies below.

8 .1 Deicing Pad Collection

EPA reviewed data on the performance of cen tralized deicing pads from a number of larger airports across the United States and Eu rope including DEN, DAY, PHL, CVG, DTW, PIT, and Oslo. These airports reported a collect ion range from 42 to 90 percent of their spent and/or applied ADF.

Additionally, the TRB Airport Cooperati ve Research Program Report No. 14, Deicing Planning Guidelines and Practices for Stormwater Management Systems, detailed airport collection efficiencies ranging from 44 to 86 percent of applied glycol (TRB Airport Cooperative Research Program, 2009).

EPA reviewed the airport-specific ADF usage data and determined that the collection of 42 to 90 percent of spent and/or applied ADF is equivalent to 61 to 90 percent of available ADF (ERG, 2011b). At proposal of this rule, EPA estimated the collection efficiency of deicing pads to be 60 percent. Based on the Agency’s new analys is, this estimate represents the lower range of collection efficiency. As a result, EPA estimates deicing pads will collect at least 60 percent of the available ADF.

8 .2 Plug and Pump Collection with GCV

EPA reviewed performance data from Gene ral Mitchell International (MKE) airport because its collection system matches the pl ug and pump with GCV collection system EPA costed for this rule. MKE reported a collecti on range between 22.5 and 33 percent of applied ADF.

Additionally, the TRB Airpor t Cooperative Research Program Report No. 14 reported collection efficiencies between 20 and 35 per cent of applied ADF for plug and pump systems (TRB Airport Cooperative Re search Program, 2009).

At proposal, EPA estimated a plug and pump with GCV collection system would collect 40 percent of available ADF. Wh en adjusted for rounding, the mean of the data above is approximately 40 percent. As such, EPA has de termined that a well-operated plug and pump system (in conjunction with GCVs) should be able to collect 40 percent of the available ADF. DCN AD01270 contains further details on thes e calculations.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 8 – Performance of Control and Treatment Scenarios

89 

### 8 .3 GCV Collection

EPA did not identify nor did commenters pr ovide collection efficiency data on GCVs alone. Gerald R. Ford International airport, whic h uses two tow-behind glycol collection units in conjunction with catch basin inserts to collect aircraft deicing contaminated stormwater around the terminal gates and apron, repor ted collecting 29 percent of all applied glycol during the 2005/2006 deicing season. Mass balance data on glycol usage and collection at Theodore Francis Green State airport between 2002 and 2006 indicate that its GCV-based system annually collects between 26 and 48 percent of all applied glycol. Overall, collection effi ciencies of applied glycol from these airports ranged from 26 to 48 pe rcent, although these systems also used some combination of catch basin inserts, plug a nd pump technology, and/or apron systems.

EPA’s data points are similar to those su mmarized in the TRB Airport Cooperative Research Program Report No. 14

. The report described collection efficiencies between 23 to 48 percent for glycol collection vehicles (TRB Airport Cooperati ve Research Program, 2009), although these systems, like those EPA referenced, also used some combination of catch basin inserts, plug and pump technology, and/or apron systems.

The ranges presented in the lite rature provide higher collec tion efficiencies than those associated with a plug and pump system; however, all of these data poin ts include technologies that would have higher collection efficiencies than a GCV alone. While EPA is unable to document the efficiency of a GCV alone, it stands to reason that the collection efficiency of a GCV alone would be less than that of a plug a nd pump with a GCV. For the purposes of today’s regulation, on a national basis, EPA assumes that a GCV is able to achieve approximately half the collection of a plug and pump with a GCV, or 20 percent of the available ADF.

8.4 AFB Treatment Performance

EPA collected data on the effectiveness of AFB treatment systems through literature review, its own sampling efforts, and industry-s upplied data. These systems have demonstrated effective treatment for targeted pollutants, including COD, BOD 5 

### , and glycol. Based on EPA’s sampling data from Albany Intern ational airport, COD was reduced by greater than 97 percent, BOD 5 

### was reduced by greater than 98 percent, and glycol was reduced by greater than 99 percent (ERG, 2007).

Influent COD concentrations that can be effi ciently treated by an AFB system range from approximately 2,000 to 128,000 mg/L and an AFB sy stem can manage brief excursions outside of this range. (See Airport Counc il International – North America comments on EPA’s Proposed Rule for Effluent Guidelines for the Airport De icing Category). EPA selected AFB as the best technology for on-site treatment of ADF-contamin ated stormwater because of the technology’s superior ability to destroy the pollutants of concern and to handle a range of influent concentrations. An evaluation of AFB treatment fo r other industrial wastewaters that have high COD content, such as distiller y, textile, dairy, and brewery wast ewaters, shows COD removals in the 50 to 98 percent range (ERG, 2010).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 8 – Performance of Control and Treatment Scenarios

90 

### 8.5 Re ferences

ERG. 2007. Memorandum from Juliana Stroup and Mary Willett (ERG) to Brian D’Amico (U.S. EPA). Aircraft Deicing Stormwater Control Tec hnologies and Their Removal Efficiencies

. (December 17). DCN AD00855.

ERG. 2010. Memorandum from Cortney Itle (ERG) to Brian D’Amico (U.S. EPA). Summary of Anaerobic Fluidized Bed Applications. (August 31). DCN AD01262.

ERG. 2011a. Memorandum from Cortney Itle an d Mary Willett (ERG) to Brian D’Amico (U.S. EPA). ADF Collection and Control Efficiency Review. (June 15). DCN AD01270.

ERG.2011b. Memorandum from Steve Strackbein and Mary Willett (ERG) to Brian D’Amico (U.S. EPA). Centralized Deicing Pad ADF Collection Efficiency . (July 12). AD01271.

TRB Airport Cooperative Resear ch Program. 2009. Deicing Planni ng Guidelines and Practices for Stormwater Management Syst ems ACRP Report No. 14. DCN AD01191.

Williams, M. 2006. Baltimore-Washington International Airport Deicing Mass Balance

.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates

91 

### 9

. P OLLUTANT 

### L OADINGS AND 

### P OLLUTANT 

### L OAD 

### R EDUCTION 

### E STIMATES


### Pollutant loadings from airport deicing ope rations are highly variable and airportspecific. Because the use of deic ing and anti-icing chemicals is weather-dependent , the pollutant loadings at each airport vary from year to year based on weather conditions and also based on each airport’s climate. In additi on, the amount of applied chemical that is discharged to surface water depends on the existing stormwater sepa ration, collection, and/or containment system present at each airport.

Due to the variations of the pollutant discha rges, EPA determined th at it would not be appropriate to develop baseline pollutant loadings using end-of -pipe monitoring data. Monitoring data on an airport’s deicing stormw ater outfall(s) provides only a “s nap shot” of a single point in time, during a monthly monitoring event or, in some cases, a single storm event. In addition, these data are available only for a select numbe r of airports and are airport-specific. Although these data provide information on the types of po llutants present in airport deicing stormwater and the range of concentrations that may reach outfall points, there is insufficient basis for extrapolating or transfer ring the data across large time frames (e .g., an entire winter season) or to other airports.

Therefore, EPA developed a pollutant lo ading estimation methodology for individual airports based on the use of ADF and airfield chemicals at the airports surveyed by EPA. The methodology takes into account EPA’s existing data s ources and provides a better estimate of the loadings than those based on sporadic monitori ng data alone. The Agency used a model-site approach to estimate loads for the Airport Deic ing Category. A model air port is an operating airport whose deicing chemical us age and unit operation and treatment information were used as parameters for the loadings model. EPA selected an airport-by-airport approach to estimate baseline loadings and loading removals from the model airports, as opposed to a more generalized approach, to better ch aracterize the current control and treatment systems in place for ADF-contaminated stormwater and to account for cu rrent site conditions a nd airport operations.

This section discusses the data sources available to EPA to support its pollutant loadings and loading reduction estimates (Section 9.1), provi des an overview of EP A’s pollutant loading methodology (Section 9.2), and desc ribes the calculation steps that compose EPA’s loading methodology (Sections 9.3 through 9.6). Section 9.7 summarizes EPA’s approach for estimating loading reductions associated w ith the discontinued use of urea as an airfield deicing chemical.

9 .1 Data Sources

EPA considered the following available data when developing the pollutant loadings estimation methodology for airport deicing operati ons (see Section 3 for more information about the data sources):

• 

### Pavement deicing chemical usage information for the 2002/2003, 2003/2004, and 2004/2005 deicing seasons, as reported by airport personnel in the airport questionnaire;

• 

### ADF purchase information for the 2002/2003, 2003/2004, and 2004/2005 deicing seasons, as reported by airline personnel in the airline detailed questionnaire;

• 

### Standard airport information available from the FAA, including the number of operations and departures by airport;Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates

92 

### • 

### Weather information for each airport from the National Oceanic and Atmospheric Administration (NOAA), including temper ature, freezing pr ecipitation, and snowfall data;

• 

### Existing airport stormwater collection a nd containment systems, as reported by airport personnel in the airport quest ionnaire or during EPA site visits;

• 

### Stan dard chemical information about ADF and pavement deicing chemicals, including molecular formul as and densities; and

• 

### Anal ytical data from EPA sampling ep isodes of airport de icing operations.

9.2 Ai rcraft Deicing Pollutant Loading

This section presents EPA’s methodology for estimating ADF pollutant loads using airline questionnaire data on ADF usage and th e theoretical oxygen demand associated with various deicing fluids.

9 .2.1 Estimate the Amount of Applied Deicing Chemical

EPA requested the purchase amount, concentr ation, and brand name in the airline detailed questionnaire for the 2002/2003, 2003/2004, and 2004/2005 deicing seasons for the following ADF chemicals:

• 

### EG Type I;

• 

### EG Type II;

• 

### EG Type IV;

• 

### PG Ty pe I;

• 

### PG Type II;

• 

### PG Ty pe III;

• 

### PG Type IV; and

• 

### Isopropyl Alcohol-Based Fluid.

Questionnaire responses provided sufficient da ta to estimate ADF usage at 56 model airports. In some cases, data were not available for every airline operating at a model airport. In these instances, EPA extrapolated the amount of ADF used at the reporting airlin es to estimate the total amount of ADF used by the entire airport, based on th e number of airport operations (departures) at the reporti ng airlines and the total am ount of airport operations. Table 9-1 presents the ADF estimates based on airline questionnaire responses. No airports reported purchasing EG Type II, EG Type III, PG Type II, PG Type III, or isopropyl alcohol-based fluid.

In addition to the ADF data reported in the airline detailed questionnaire, 10 airports reported their estimates of total annual ADF usage to EPA in the comment section of the airport questionnaire (see Table 9-2 ). These ADF data were combined w ith the ADF data reported in the airline detailed questi onnaires, resulting in 66 airports with total PG/EG (gallons) usage estimates. EPA used the airport’s estimate of AD F usage from the airport questionnaires because those data came from a certi fied questionnaire response.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates

93 

### Table 9-1. ADF Estimates Based on Air line Detailed Questionnaire Responses

Airport ID Airport Name Estimated PG/EG Use (GPY) PG Type I

(%) PG Type IV

(%) EG Type 1

(%) EG Type IV

(%)
1003 Ketchikan International 18,182 0 0 100 0
1006 Chicago O'Hare International 1,516,626 80 20 0 0
1010 Fairbanks International 83,335 0 0 100 0
1011 Lambert - St Louis International 325,122 23 1 70 6
1012 Ted Stevens Anchorage International 420,735 0 0 100 0
1013 Wiley Post-Will Rogers Mem 3,056 9 0 91 0
1021 Buffalo Niagara International 281,836 92 9 0 0
1022 Fort Wayne International 50,412 92 8 0 0
1024 Indianapolis International 452,155 91 9 0 0
1026 Dallas/Fort Worth International 166,790 43 12 38 7
1028 Denver International 1,043,138 87 10 4 0
1029 La Guardia 485,157 75 22 2 1
1036 Baltimore - Washington International 323,623 90 10 0 0

1037 George Bush Intercontinental Airport/Houston 10,242 82 18 0 0

1043 Ralph Wien Memorial 2,500 27 0 73 0
1047 Sacramento Mather 1,282 100 0 0 0
1053 General Edward Lawrence Logan International 995,249 82 17 0 0

1058 Gerald R Ford International 98,156 86 13 0 0
1059 Greater Rochester International 229,158 91 9 0 0
1065 Albany International 125,775 93 7 0 0
1066 Salt Lake City International 570,540 22 6 52 20
1069 Cleveland - Hopkins International 582,321 90 10 0 0
1074 South Bend Regional 29,586 75 25 0 0
1079 Manchester 177,307 87 13 0 0
1080 Syracuse Hancock International 186,351 97 3 0 0
1089 John F Kennedy International 560,031 82 18 0 0
1095 Chicago Midway International 293,834 88 12 0 0
1100 Toledo Express 46,449 64 5 29 2
1103 Juneau International 48,014 0 0 100 0
1104 Nome 3,047 15 0 85 0
1105 Spokane International 67,984 92 8 0 0
1107 Pittsburgh International 943,982 88 12 0 0
1109 Airborne Airpark 432,416 74 26 0 0
1110 Aniak 476 100 0 0 0
1111 Port Columbus International 288,374 92 8 0 0
1113 Cincinnati/Northern Kentucky International 715,836 24 5 61 11Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates



### Table 9-1 (Continued)

94 Airport ID Airport Name Estimated PG/EG Use (GPY) PG Type I

(%) PG Type IV

(%) EG Type 1

(%) EG Type IV

(%)
1117 Cherry Capital 11,524 75 0 0 25
1118 Bethel 4,897 40 0 60 0
1123 James M Cox Dayton International 90,580 89 11 0 0
1124 Des Moines International 79,658 84 14 3 0
1126 Minneapolis/ St Paul International/Wold - Chamberlain 1,456,537 93 7 0 0

1128 Charlotte/Douglas International 143,572 81 19 0 0
1129 Bradley International 427,068 88 12 0 0
1136 General Mitchell International 152,944 90 9 0 1
1138 Detroit Metropolitan Wayne County 2,152,292 93 7 0 0
1139 Philadelphia International 979,983 88 12 0 0
1140 Memphis International 199,174 88 12 0 0
1141 Ronald Reagan Washington National 219,533 81 16 3 0
1142 Washington Dulles International 1,076,083 77 22 1 0
1145 Newark Liberty International 1,123,057 86 14 0 0
1148 Kansas City International 203,726 75 8 17 0
1149 Fort Worth Alliance 1,522 97 3 0 0
1150 Greater Rockford 146,856 79 21 0 0
1151 Kalamazoo/Battle Creek International 22,002 84 16 0 0

1152 Duluth International 68,168 96 4 0 0
1153 Akron - Canton Regional 60,246 90 10 0 0 Source: Airport Deicing Operations ADF Usage Database (USEPA, 2008). Note: PG/EG gallons represent total usage normalized to 100 percent glycol. Values may not sum to 100 due to rounding. GPY – Gallons per year.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates 

### Table 9-2. ADF Data Reported in the Airport Questionnaire

Airport ID Airport Name PG/EG Usage (GPY)
1115 Jacksonville International 1,000
1062 Birmingham International 5,000
1072 Gillette-Campbell County 880
1060 Williamson County Regional 150
1096 Santa Fe Municipal 1,108
1097 Lovell Field 4,148
1025 Tupelo Regional 820
1143 San Francisco International 105
1001 Montgomery Regional (Dannelly Field) 232
1019 Ontario International 35 Source: Airport Deicing Operations ADF Usage Database (USEPA, 2008). GPY – Gallons per year.



### Using the airline and airpor t questionnaire data on ADF pur chases, airport departures, and climate, EPA correlated the estimate of the amount of ADF used to the climate and size of each airport. EPA created an “ADF Factor” to es timate the relative amount of deicing occurring at each airport based on the airport’s climate a nd number of departures. EPA calculated the ADF Factor by multiplying the 30-year annual averag e number of SOFP days by the average number of annual departures at each airport duri ng 2004-2006 (USEPA, 2008a). EPA graphed the total gallons of PG/EG purchased with the ADF factor and determined the equation of the line. During this analysis, EPA noted a diffe rence in the relationship of ADF Factor and ADF usage for Alaskan airports compared to other airports. Du e to this difference, EPA developed a separate graph and equation for Alaskan airports. Figure 9-1 shows the graph for non-Alaskan airports and Figure 9-2 presents the graph for Alaskan airports.

y = 0.3073x
R

2 = 0.7622

0 500,000 1,000,000 1,500,000 2,000,000 2,500,000

0 2,000,000 4,000,000 6,000,000 8,000,000

ADF Factor (SOFP Days x Average Annual Departures) PG/EG Gallons per Year



### Figure 9-1. ADF Factor vs. PG/EG Gallons for U.S. Airports (excluding Alaska)

95Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates

y = 0.0632x
R 2 = 0.7031

0 100,000 200,000 300,000 400,000 500,000

0 2,000,000 4,000,000 6,000,000

ADF Factor (SOFP Days x Average Annual Departures) PG/EG Gallons Per Year



### Figure 9-2. ADF Factor vs. PG/EG Gallons for Alaskan Airports

EPA used the line equations to estimate the to tal gallons of ADF used at model airports that did not have available ADF data in the ai rport or airline detailed questionnaires. Based on the estimated total gallons of ADF used at an ai rport, EPA calculated the distribution of different types of ADF (PG/EG, Type I/Type IV) based on the average percent dist ribution of the reported ADF amounts. See the Airport Deicing Loadings Calculations memorandum (ERG, 2008b) for more detail. Table 9-3 presents the final estimates of ADF us age for airports in the scope of the final rule.

96Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates

97 

### Table 9-3. ADF Annual Usage Esti mates for In-scope Airports

Airport ID Airport Name PG Type I (gallons) PG Type IV (gallons) EG Type I (gallons) EG Type IV (gallons)
1001 Montgomery Regional (Dannelly Field) 166 22 41 3
1003 Ketchikan International 0 0 18,182 0
1004 Norfolk International 22,084 2,938 5,451 402
1006 Chicago O'Hare International 1,213,301 303,325 0 0
1007 Yeager 35,450 4,715 8,750 646
1008 Tucson International 1,675 223 413 31
1010 Fairbanks International 0 0 83,335 0
1011 Lambert-St Louis International 74,778 3,251 227,586 19,507
1012 Ted Stevens Anchorage International 0 0 420,735 0
1014 Albuquerque International Sunport 46,107 6,133 11,380 840
1015 Gulfport-Biloxi International 1,109 148 274 20
1017 Austin Straubel International 44,442 5,912 10,969 810
1018 Piedmont Triad International 49,169 6,540 12,136 896
1019 Ontario International 25 3 6 0
1020 Hartsfield - Jackson Atlanta International 259,100 34,465 63,950 4,720

1021 Buffalo Niagara International 259,289 25,365 0 0
1022 Fort Wayne International 46,379 4,033 0 0
1023 Seattle-Tacoma International 112,631 14,982 27,799 2,052
1024 Indianapolis International 411,461 40,694 0 0
1026 Dallas/Fort Worth International 71,720 20,015 63,380 11,675
1028 Denver International 907,530 104,314 41,726 0
1029 La Guardia 363,868 106,735 9,703 4,852
1031 Richmond Internationa l 42,442 5,646 10,476 773
1032 Austin-Bergstrom International 17,198 2,288 4,245 313
1033 Mc Carran International 7,613 1,013 1,879 139
1034 Metropolitan Oakland International 0 0 0 0
1035 San Diego International 0 0 0 0
1036 Baltimore-Washington International 291,261 32,362 0 0
1037 George Bush Intercontinental Airport/Houston 8,399 1,844 0 0

1040 Louis Armstrong New Orleans International 0 0 0 0

1041 Glacier Park International 27,578 3,668 6,807 502
1043 Ralph Wien Memorial 675 0 1,825 0
1044 Roanoke Regional/Woodrum Field 23,552 3,133 5,813 429
1045 Norman Y. Mineta San Jose International 10 0 0 0

1046 Long Island Mac Arthur 31,135 4,141 7,685 567
1050 Aspen-Pitkin Co/Sardy Field 10,742 1,429 2,651 196
1052 Wilmington International 1,556 207 384 28Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates



### Table 9-3 (Continued)

98 Airport ID Airport Name PG Type I (gallons) PG Type IV (gallons) EG Type I (gallons) EG Type IV (gallons)
1053 General Edward Lawrence Logan International 816,104 169,192 0 0

1054 Jackson Hole 24,413 3,247 6,026 445
1057 Will Rogers World 35,409 4,710 8,740 645
1058 Gerald R. Ford International 84,414 12,760 0 0
1059 Greater Rochester International 208,534 20,624 0 0
1061 William P Hobby 10,134 1,348 2,501 185
1062 Birmingham Internatio nal 3,578 476 883 65
1063 Evansville Regional 14,412 1,917 3,557 263
1065 Albany International 116,971 8,804 0 0
1066 Salt Lake City International 125,519 34,232 296,681 114,108
1067 Helena Regional 13,147 1,749 3,245 240
1068 Eppley Airfield 79,386 10,560 19,594 1,446
1069 Cleveland-Hopkins International 524,089 58,232 0 0
1070 City of Colorado Springs Municipal 54,230 7,214 13,385 988
1074 South Bend Regional 22,189 7,396 0 0
1075 Pensacola Regional 592 79 146 11
1078 Nashville International 65,479 8,710 16,161 1,193
1079 Manchester 154,257 23,050 0 0
1080 Syracuse Hancock International 180,760 5,591 0 0
1081 Bob Hope 0 0 0 0
1083 Tampa International 0 0 0 0
1084 Bismarck Municipal 15,018 1,998 3,707 274
1086 Palm Beach Interna tional 732 97 181 13
1087 El Paso International 11,608 1,544 2,865 211
1088 Outagamie County Region al 41,375 5,504 10,212 754
1089 John F Kennedy International 459,225 100,806 0 0
1090 Boise Air Terminal/Gowen Fld 51,086 6,795 12,609 931
1091 Rochester International 24,717 3,288 6,101 450
1094 Boeing Field/King County International 3,688 491 910 67
1095 Chicago Midway International 258,574 35,260 0 0
1097 Lovell Field 2,968 395 733 54
1099 Sacramento International 0 0 0 0
1100 Toledo Express 29,728 2,322 13,470 929
1101 Portland International 80,173 10,664 19,788 1,461
1102 John Wayne Airport-Orange County 0 0 0 0
1103 Juneau International 0 0 48,014 0
1104 Nome 457 0 2,590 0
1105 Spokane International 62,545 5,439 0 0Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates



### Table 9-3 (Continued)

99 Airport ID Airport Name PG Type I (gallons) PG Type IV (gallons) EG Type I (gallons) EG Type IV (gallons)
1107 Pittsburgh International 830,704 113,278 0 0
1108 Louisville International-Standiford Field 91,849 12,217 22,670 1,673
1111 Port Columbus International 265,304 23,070 0 0
1113 Cincinnati/Northern Kentucky International 171,801 35,792 436,660 78,742

1114 Stewart International 23,086 3,071 5,698 421
1115 Jacksonville International 716 95 177 13
1116 Reno/Tahoe International 53,382 7,101 13,176 973
1117 Cherry Capital 8,643 0 0 2,881
1118 Bethel 1,959 0 2,938 0
1119 Rickenbacker International 7,661 1,019 1,891 140
1120 Rapid City Regional 18,185 2,419 4,488 331
1121 Theodore Francis Green State 107,383 14,284 26,504 1,956
1122 Southwest Florida International 680 90 168 12
1123 James M Cox Dayton International 80,616 9,964 0 0
1124 Des Moines International 66,913 11,152 2,390 0
1126 Minneapolis/St Paul International/WoldChamberlain 1,354,580 101,958 0 0

1128 Charlotte/Douglas International 116,293 27,279 0 0
1129 Bradley International 375,820 51,248 0 0
1130 San Antonio International 9,119 1,213 2,251 166
1131 Wilkes-Barre/Scranton International 30,426 4,047 7,510 554
1133 Phoenix Sky Harbor International 0 0 0 0
1135 Lafayette Regional 1,065 142 263 19
1136 General Mitchell International 137,650 13,765 0 1,529
1137 Dallas Love Field 26,622 3,541 6,571 485
1138 Detroit Metropolitan Wayne County 2,001,632 150,660 0 0
1139 Philadelphia International 862,385 117,598 0 0
1140 Memphis International 175,273 23,901 0 0
1141 Ronald Reagan Washington National 177,822 35,125 6,586 0
1142 Washington Dulles International 828,584 236,738 10,761 0
1143 San Francisco International 75 10 19 1
1144 Central Wisconsin 31,203 4,151 7,702 568
1145 Newark Liberty International 965,829 157,228 0 0
1146 Northwest Arkansas Regional 22,013 2,928 5,433 401
1147 Raleigh-Durham International 73,281 9,748 18,087 1,335
1148 Kansas City International 152,794 16,298 34,633 0 Source: Airport Deicing Operations ADF Usage Database (USEPA, 2008). Note: Values may not sum to total usage amounts due to rounding.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates

100 

### 9 .2.2 Calculate the Amount of Pollutant L oad Associated with the Applied ADF

As aircraft deicing chemicals break down in the environment, they increase COD and BOD. EPA calculated the amount of COD and BOD (presented as-5 day BOD, or BOD 5 

### ) associated with the degradation of the applied deicing/anti-icing chemicals.

EPA considered two approaches to estimate the amount of COD and BOD 5 

### associated with deicing chemicals. The first approach i nvolved using laboratory empirical COD and BOD 5 

### data for deicing chemicals. The second approach involved using standard chemical information and stoichiometric equations to estimate COD and BOD 5 

### for each chemical.

EPA determined it would not be suitable to use empirical data to estimate loadings for three main reasons. First, empirical COD and BOD 5 

### data were not readily available for all deicing/anti-icing chemicals. Second, the availa ble empirical data were outdated and brandspecific. Finally, chemical formulations vary significantly over time and by brand, so it is inappropriate to apply any give n set of empirical data to a ll airports and chemicals.

EPA selected the second approach, calcula ting loadings based on standard chemical information and stoichiometric equations. The advantage of this methodology over using empirical data is that it can be used for al l deicing chemicals. In addition, this methodology allows the calculations and assumptions used to be clearly presented. EPA checked the validity of the COD and BOD 5 

### concentrations for PG and EG calcu lated using this methodology against the available empirical data and found a good match.

Calculate the Total Mass of Each Pollutant

First, EPA estimated the total mass of each chemical based on the airline and airport questionnaire responses (which sp ecified varying formulations of ADF and deicing products). To calculate the total mass of applied chemical, EP A multiplied the reported mass of each chemical by the reported percentage of the pollutant in the ADF formulation, by the density of the pollutant.

Determine the Theoretical Oxyge n Demand of Each Chemical

Next, EPA determined the theoretical oxyge n demand (ThOD) associated with the degradation of each of the de icing chemicals. The ThOD estimate was based on the molecular formula of the chemical and the stoichiometric equation of the breakdown of the chemical to the end products of carbon dioxide and water. Table 9-4 lists the calculated ThOD for each chemical in aircraft deicers.

Table 9-4. Theoretical Oxygen Demand Calcul ations for Aircraft Deicing Chemicals

Deicing Compound Molecular Formula Stoichiometric Formula ThOD (Moles of O 2 per Mole of Deicin g Compound)
PG C 3 H 8 O 2 C 3 H 8 O 2 + 4 O 2 Æ 3 CO 2 + 4 H 2 O 4.0
EG C 2 H 6 O 2 2[C 2 H 6 O 2 ] + 5 O 2 Æ 4 CO 2 + 6 H 2 O 2.5Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates 

### Determine the COD of Each Chemical

EPA next determined the COD loading associ ated with the chemical’s degradation. EPA assumed that the chemical would completely degr ade in the environment over time and therefore the calculated ThOD load would be equivalent to the COD load. EPA estimated the COD load associated with each reported chemical based on the calculated mass of the chemical purchased, the molecular weight of the chemical, the ThOD, and the molecular weight of oxygen, using the equation below:

grams 434 pound
O of moles O of grams Weight Molecular O chemical of moles O of moles ThOD chemical of grams chemical of moles Weight Molecular Chemical pound grams 434 (pounds) Chemical (pounds) Load COD

2 2 2 2 × ⎟ ⎠ ⎞ ⎜ ⎝ ⎛

× ⎟ ⎠ ⎞ ⎜ ⎝ ⎛

× ⎟ ⎟ ⎠ ⎞ ⎜ ⎜ ⎝ ⎛

× × = 

### (9-1)

Determine the BOD 5 

### of Each Chemical

EPA calculated the BOD 5 

### loading of ADF based on the estimated COD loading in ADF. EPA developed an industry-specific relationship between COD and BOD 5 

### using analytical data for untreated deicing stormwat er from the EPA sampling episodes at Albany International airport, Pittsburgh Intern ational airport, and Denver Inte rnational airport. The average COD/BOD 5 

### ratio was 1.67. This relationship was used to calculate the BOD 5 

### associated with the degradation of the deic ing chemical. See the Airport Deicing Loading Calculations memorandum (ERG, 2008b) for more information.

9 .2.3 Estimate the Amount of Baseline Pollutant Load that is Discharged Directly

The amount of applied chemical that is di scharged directly is airport-specific and dependent upon the existing stormw ater collection /treatment system present at each airport. Typically, ADF is applied at a number of specifi c locations at the airport, including gates, deicing pads, and/or aprons.

In estimating the direct discharge amount of ADF, EPA first estimated the amount of applied ADF that would be available for discha rge. EPA assumed that 75 percent of applied Type I ADF falls onto the pavement at the deic ing area and is available for discharge; the remaining 25 percent is lost to ev aporation, wind, or tire tracking, or adheres to the plane and is later sheared off during taxiing and takeoff (S witzenbaum, et al., 1999). EPA assumed that 10 percent of Type IV ADF falls to the pavement in the deicing area and is available for discharge; the remaining 90 percent adheres to the plane. The Agency multiplied the total amount of applied ADF by the appropriate percentage available for discharge to determine the amount of ADF that is available for discharge.

Next, EPA determined the percen tage of available ADF that w ould be directly discharged at each airport, depending on the airport’s cu rrent control and treatment systems (ERG, 2011). EPA estimated collection and control percentage s of available ADF for each airport based on information provided during EPA site visits and in the airport ques tionnaire. If the airport did not provide an ADF collection and control percen tage estimate, EPA personnel reviewed the airport’s questionnaire responses and the reported collection and control percentage of similar systems to determine an es timate for the airport.

101Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates

102 

### The COD load associated with each ADF chem ical applied at an airport was reduced by EPA’s estimate of the airport’s current collection and control pe rcentage to estimate the amount of COD directly discharged. These estimates re present the baseline amou nt of ADF discharged to the environment. Table 9-5 in Section 9.2.5 presents EPA’s es timate of the baseline COD load (in pounds) directly discharg ed by each airport.

9 .2.4 Estimate Pollutant Loading Discharges for Each ADF Collection/Control Scenario

Two of EPA’s regulato ry options require a specific collection and treatment percentage of available ADF. For the final rule, EPA evaluated the following scenarios as discussed in Section 11:

• 

### 20% Collection and Control Scenario: coll ection and treatment of 20 percent of available ADF; and

• 

### 40% Collection and Control Scenario: coll ection and treatment of 40 percent of available ADF.

EPA estimated the direct discharge COD load of each collection and control scenario accounting for the following two components:

• 

### The COD load associated with the app lied ADF, minus any reductions achieved by the collection and control practices implemented; and

• 

### The C OD load that would be discharged from AFB biological treatment of the collected treatment.

EPA estimated the amount of COD load that would be discharged from treatment for each airport that had load reductions in a scen ario. Using analytical data from its sampling episodes, EPA determined that AFB systems remove 97.5 percent of COD. Therefore, EPA assumed that 97.5 percent of the COD load going to treatment would be removed and 2.5 percent would be discharged.

9.2.5 Estimate Pollutant Loading Reductions for Each ADF Collection/Control Scenario

After estimating the loads for each scenari o, EPA estimated the loading reductions as compared to baseline. Table 9-5 lists the ADF COD baseline loads and reductions for each control and treatment scenario EPA evaluated for t hose airports in the scope of the final rule.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates

103 

### Table 9-5. ADF COD Baseline Loads and Load ing Reductions for Each Control and Treatment Scenario, by In-Scope Airport

Airport ID Airport Airport Weighting

Factor Current ADF Collection (%) Baseline COD Load

(pounds) COD Load Reduction for 20% Collection

and Control

Scenario (pounds) COD Load Reduction for 40% Collection

and Control

Scenario (pounds)
1001 Montgomery Regional (Dannelly Field) 6.7013 0 2,214 432 863

1003 Ketchikan International 1.0000 NA 0 0 0
1004 Norfolk International 1.0000 20 235,637 0 57,436
1006 Chicago O'Hare International 1.0000 40 8,204,552 0 0
1007 Yeager 2.1508 40 283,685 0 0
1008 Tucson International 2.9997 20 17,873 0 4,357
1010 Fairbanks International 1.0000 ≥ 60 299,205 0 0
1011 Lambert-St Louis International 1.0000 ≥ 60 1,154,584 0 0
1012 Ted Stevens Anchorage International 1.0000 40 2,265,902 0 0

1014 Albuquerque International Sunport 1.0000 20 491,959 0 119,915

1015 Gulfport-Biloxi International 5.8413 ≥ 60 0 0 0
1017 Austin Straubel International 2.3269 40 355,646 0 0
1018 Piedmont Triad International 1.0000 0 655,787 127,879 255,757
1019 Ontario International 1.0000 0 334 200 200
1020 Hartsfield - Jackson Atlanta International 1.0000 ≥ 60 1,382,287 0 0

1021 Buffalo Niagara International 1.0000 40 1,718,928 0 0
1022 Fort Wayne International 1.9682 0 511,705 102,341 204,682
1023* Seattle-Tacoma International 1.0000 0 1,502,208 292,931 585,861
1024 Indianapolis International 1.0000 40 2,728,125 0 0
1026 Dallas/Fort Worth International 1.0000 ≥ 60 557,682 0 0
1028 Denver International 1.0000 ≥ 60 104,244 0 0
1029 La Guardia 1.0000 0 4,216,728 822,262 1,644,524
1031 Richmond Internationa l 1.0000 40 339,643 0 0
1032 Austin-Bergstrom International 1.0000 40 137,629 0 0
1033 Mc Carran International 1.0000 40 60,923 0 0
1034 Metropolitan Oakland International 1.0000 ≥ 60 0 0 0

1035 San Diego International 1.0000 ≥ 60 0 0 0
1036 Baltimore-Washington International 1.0000 ≥ 60 1,289,506 0 0

1037 George Bush Intercontinental Airport/Houston 1.0000 40 56,571 0 0

1040 Louis Armstrong New Orleans International 1.0000 ≥ 60 0 0 0Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates



### Table 9-5 (Continued)

104 Airport ID Airport Airport Weighting

Factor Current ADF Collection (%) Baseline COD Load

(pounds) COD Load Reduction for 20% Collection

and Control

Scenario (pounds) COD Load Reduction for 40% Collection

and Control

Scenario (pounds)
1041 Glacier Park International 3.1409 0 367,815 71,724 143,448
1043 Ralph Wien Memorial 1.0000 0 23,743 4,630 9,260
1044 Roanoke Regional/Woodrum Field 2.1921 0 314,124 61,254 122,508

1045 Norman Y. Mineta San Jose International 1.0000 10 0 0 0

1046 Long Island Mac Arthur 1.9985 ≥ 60 166,102 0 0
1050 Aspen-Pitkin Co/Sardy Field 4.7500 40 85,963 0 0
1052 Wilmington International 6.0388 0 20,756 4,047 8,095
1053 General Edward Lawrence Logan International 1.0000 0 9,147,072 1,783,679 3,567,358

1054 Jackson Hole 4.3500 ≥ 60 0 0 0
1057 Will Rogers World 1.0000 0 472,260 92,091 184,181
1058 Gerald R. Ford International 1.5862 40 563,544 0 0
1059 Greater Rochester International 1.0000 50 1,152,208 0 0
1061 William P Hobby 1.0000 ≥ 60 0 0 0
1062 Birmingham International 2.8410 0 47,717 9,305 18,610
1063 Evansville Regional 5.1042 0 192,217 37,482 74,965
1065 Albany International 1.0000 ≥ 60 25,771 0 0
1066 Salt Lake City International 1.0000 ≥ 60 1,687,338 0 0
1067 Helena Regional 4.2000 ≥ 60 0 0 0
1068 Eppley Airfield 1.0000 0 1,058,801 206,466 412,933
1069 Cleveland-Hopkins International 1.0000 40 3,480,467 0 0

1070 City of Colorado Springs Municipal 1.7414 40 433,971 0 0

1074 South Bend Regional 2.1417 ≥ 60 0 0 0
1075 Pensacola Regional 3.9341 ≥ 60 0 0 0
1078 Nashville International 1.0000 ≥ 60 349,329 0 0
1079 Manchester 1.0000 0 1,715,962 334,613 669,225
1080 Syracuse Hancock International 1.0000 ≥ 60 791,854 0 0
1081 Bob Hope 1.0000 ≥ 60 0 0 0
1083 Tampa International 1.0000 ≥ 60 0 0 0
1084 Bismarck Municipal 3.8679 0 200,305 39,059 78,119
1086 Palm Beach International 1.0000 ≥ 60 0 0 0
1087 El Paso International 3.0457 ≥ 60 0 0 0
1088 Outagamie County Regional 2. 4841 0 551,842 107,609 215,218Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates



### Table 9-5 (Continued)

105 Airport ID Airport Airport Weighting

Factor Current ADF Collection (%) Baseline COD Load

(pounds) COD Load Reduction for 20% Collection

and Control

Scenario (pounds) COD Load Reduction for 40% Collection

and Control

Scenario (pounds)
1089 John F Kennedy International 1.0000 0 5,155,239 1,005,272 2,010,543
1090 Boise Air Terminal/Gowen Fld 1.5043 ≥ 60 272,543 0 0
1091 Rochester International 3.1749 40 197,799 0 0
1094 Boeing Field/King County International 5.8985 40 29,510 0 0

1095 Chicago Midway International 1.0000 ≥ 60 0 0 0
1097 Lovell Field 4.9996 0 39,586 23,752 23,752
1099 Sacramento International 1.0000 20 0 0 0
1100 Toledo Express 2.0917 20 359,704 0 87,678
1101 Portland International 1.0000 20 855,437 0 208,513
1102 John Wayne Airport-Orange County 1.0000 ≥ 60 0 0 0

1103 Juneau International 1.0000 0 430,969 84,039 168,078
1104 Nome 1.0000 0 28,231 5,505 11,010
1105 Spokane International 1.5192 ≥ 60 0 0 0
1107 Pittsburgh International 1.0000 ≥ 60 3,689,998 0 0
1108 Louisville InternationalStandiford Field 1.0000 ≥ 60 490,009 0 0

1111 Port Columbus International 1.0000 0 2,927,149 570,794 1,141,588
1113 Cincinnati/Northern Kentucky International 1.0000 ≥ 60 415,766 0 0

1114 Stewart International 2.8661 40 184,745 0 0
1115 Jacksonville International 1.0000 ≥ 60 0 0 0
1116 Reno/Tahoe International 1.0000 20 569,580 0 138,835
1117 Cherry Capital 3.5400 ≥ 60 0 0 0
1118 Bethel 1.0000 0 47,733 9,308 18,616
1119 Rickenbacker International 4.3659 0 102,180 19,925 39,850
1120 Rapid City Regional 3.1082 0 242,540 47,295 94,591
1121 Theodore Francis Green State 1.0000 ≥ 60 572,884 0 0
1122 Southwest Florida International 1.0000 ≥ 60 0 0 0
1123 James M Cox Dayton International 1.0000 ≥ 60 357,499 0 0

1124 Des Moines International 1.6211 40 460,483 0 0
1126 Minneapolis/St PaulInternational/WoldChamberlain 1.0000 ≥ 60 5,968,923 0 0

1128 Charlotte/Douglas International 1.0000 0 1,308,047 255,069 510,138
1129 Bradley International 1.0000 ≥ 60 1,669,398 0 0Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates



### Table 9-5 (Continued)

106 Airport ID Airport Airport Weighting

Factor Current ADF Collection (%) Baseline COD Load

(pounds) COD Load Reduction for 20% Collection

and Control

Scenario (pounds) COD Load Reduction for 40% Collection

and Control

Scenario (pounds)
1130 San Antonio International 1.0000 0 121,626 23,717 47,434
1131 Wilkes-Barre/Scranton International 2.6815 0 405,801 79,131 158,262

1133 Phoenix Sky Harbor International 1.0000 20 0 0 0

1135 Lafayette Regional 6.6425 0 14,201 8,521 8,521
1136 General Mitchell International 1.0000 44 852,970 0 0
1137 Dallas Love Field 1.0000 40 213,039 0 0
1138 Detroit Metropolitan Wayne County 1.0000 ≥ 60 0 0 0

1139 Philadelphia International 1.0000 ≥ 60 1,436,522 0 0
1140 Memphis International 1.0000 0 1,946,410 379,550 759,100
1141 Ronald Reagan Washington National 1.0000 40 1,229,789 0 0

1142 Washington Dulles International 1.0000 40 5,686,802 0 0

1143 San Francisco International 1.0000 ≥ 60 0 0 0
1144 Central Wisconsin 3.0156 0 416,170 81,153 162,306
1145 Newark Liberty Intl 1.0000 0 10,762,687 2,098,724 4,197,448
1146 Northwest Arkansas Regional 1.8782 0 293,595 57,251 114,502
1147 Raleigh-Durham Intl 1.0000 0 977,382 190,589 381,179
1148 Kansas City Intl 1.0000 40 1,200,632 0 0 NA – Ketchikan was sent an airport questionnaire but did not respond. Sources: Airport Deicing Loadings Database. (USEPA, 2010); ADF Capture and Co ntrol Efficiency Review Memorandum. (ERG, 2011) * The airport post-questionnaire has installed deicing pads; high BOD stormwater is sent to a POTW.



### For each scenario, EPA estimated no load re ductions for the airport if it collects and controls more than the required percentage of available ADF (e .g., for the 20 percent efficiency scenario, if an airport currently collects and controls 20 percen t or more of available ADF, no load reductions were estimated for the airport). Model airports that curre ntly collect the required percentage of available ADF either treat it to the required discharge levels, discharge the collected ADF to a POTW, or send it off-site a nd are assumed to be in compliance with any numeric effluent limitation.

EPA assumed that airports that used small quantities of ADF (less than 5,000 gallons of normalized ADF), as described below in Sectio n 10.1, would collect and ha ul away the required percentage of ADF instead of collecting it for on -site treatment. For more information, refer to the Airport Deicing Loadings Calculations memorandum (ERG, 2008b).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates

107 

### 9.3 Ai rfield Deicing Pollutant Loading

This section presents EPA’s methodology for estimating airfield deicing pollutant loads using airport questionnaire data on airfield chemical use.

9.3 .1 Estimate the Amount of Applied Deicing Chemical

In the airport questionnaire, EPA requested that airport personnel report the usage amount, concentration, and brand name of the following pavement deicing materials for the 2002/2003, 2003/2004, and 2004/2005 deicing seasons:

• 

### Ur ea;

• 

### Potassium Acetate;

• 

### CMA;

• 

### Sodium Acetate;

• 

### Sand;

• 

### Sodium Formate;

• 

### EG- Based Fluids;

• 

### PG- Based Fluids; and

• 

### Other : (Specify).

EPA evaluated the data provided for each reported chemical to determine the most appropriate way to estimate the average amount us ed over the three winter seasons reported. In addition, EPA read the comments provided by the airport personnel to determine any extenuating circumstances that affect chemical use. For ex ample, airport personnel ma y have reported that urea was replaced with potassium acetate at the ai rport during the three years reported. In this case, EPA used the potassium acetate average in th e loadings estimate and did not use any of the urea data to better represent the airport’s current practices. Nine ty airports reported pavement deicing chemical usage values to EP A in their questionnaire responses.

Table 9-6 shows the three-year average pavement deicing chemical usage EPA calculated from the reported data (normalized to pur e chemical) by airport and chemical. In the questionnaire, airports reported poun ds or gallons of pavement deicing chemical used along with the concentration of the chemical . If airport personnel reported a volume of chemical in the airport or airline detailed questionnaire, EPA multiplied the reported volume by the reported deicing chemical strength and the chemical density.

No airports reported using CMA. Multiple air ports reported using sand, but these data are not included in Table 9-6 , because sand was not included in the loads analysis. Only one airport reported using granular potassium acetate. Potassium acetate (in the liquid form) is the most commonly used pavement deicing chemical.108Technical Development Document for EffluentLimitation Guidelines and Standards for the Airport Deicing CategorySection 9 – Pollutant Loadings andPollutant Load Reduction EstimatesTable 9-6. Three-Year Average Amount of Pavement Deicing Chemical Usage, in PoundsAirportIDAirport NameEG-BasedFluidsGranularPotassiumAcetatePotassiumAcetateSodiumAcetateSodiumFormatePG-BasedFluidsUrea1006Chicago O'Hare Intl00655,284004,681,46201007Yeager0002,560011,54027,5171010Fairbanks Intl00197,024000332,0001011Lambert - St Louis Intl005,119,50200001012Ted Stevens Anchorage Intl001,266,4170002,514,9001013Wiley Post-Will Rogers Mem00000020,0001014Albuquerque Intl Sunport004,58600001016Tri - State/Milton J Ferguson Field0027,08900056,0001017Austin Straubel Intl0038,12100044,8601018Piedmont Triad Intl0053,93800092,6671020Hartsfield - Jackson Atlanta Intl00314,45600001021Buffalo Niagara Intl00007,760001022Fort Wayne Intl00268,772000285,5441023Seattle - Tacoma Intl0097,9146960001024Indianapolis Intl00783,038470,6670001026Dallas/Fort Worth Intl0018,17900001028Denver Intl003,526,70400001029La Guardia001,118,1451,6760442,70001031Richmond Intl00284,77017,0000001032Austin - Bergstrom Intl0017,48300001036Baltimore - Washington Intl001,178,861257,280156,800001041Glacier Park Intl0000003331043Ralph Wien Memorial0038,87000010,0001044Roanoke Regional/Woodrum Field00109,04400001050Aspen - Pitkin County/Sardy Field017,00046,73200001052Wilmington Intl00000001053General Edward Lawrence Logan Intl1,217,3000000010,217109Technical Development Document for EffluentLimitation Guidelines and Standards for the Airport Deicing CategorySection 9 – Pollutant Loadings andPollutant Load Reduction EstimatesTable 9-6 (Continued)AirportIDAirport NameEG-BasedFluidsGranularPotassiumAcetatePotassiumAcetateSodiumAcetateSodiumFormatePG-BasedFluidsUrea1057Will Rogers World0049,6032,9100001058Gerald R Ford Intl0066,34108,568001059Greater Rochester Intl00294,63400001063Evansville Regional0029,06500001065Albany Intl00196,535148,5000001066Salt Lake City Intl00173,1690001,121,2321068Eppley Airfield00289,2889,4740001069Cleveland – Hopkins Intl002,456,657190,0556,117001070City of Colorado Springs Municipal00224,59800001071Tweed - New Haven0002910001074South Bend Regional00000032,4401078Nashville Intl00163,77900001079Manchester00398,78000036,8331080Syracuse Hancock Intl0011,79200001082Trenton Mercer0012,39304,704001084Bismarck Municipal0016,11400001085Waterloo Municipal0000006,0001088Outagamie County Regional00229,29000001089John F Kennedy Intl00170,3303,460,8310224,79201090Boise Air Terminal/Gowen Field0098,582000269,9011094Boeing Field/King County Intl0010,25500001095Chicago Midway Intl001,397,27400001098Aberdeen Regional0017,48900001100Toledo Express00240,20900001101Portland Intl00256,47810,292211,183001103Juneau Intl000000478,000110Technical Development Document for EffluentLimitation Guidelines and Standards for the Airport Deicing CategorySection 9 – Pollutant Loadings andPollutant Load Reduction EstimatesTable 9-6 (Continued)AirportIDAirport NameEG-BasedFluidsGranularPotassiumAcetatePotassiumAcetateSodiumAcetateSodiumFormatePG-BasedFluidsUrea1104Nome0039,30700001105Spokane Intl0024000951498,0001107Pittsburgh Intl001,198,42513,33389,507001108Louisville Intl - Standiford Field00762,0200109,760001109Airborne Airpark001,916,87701,809,373001110Aniak0000002,4001111Port Columbus Intl00623,77307,161001112Deadhorse0012,22900020,0001113Cincinnati/Northern Kentucky Intl003,050,21804,000001114Stewart Intl0078,6142,52000151,8001116Reno/Tahoe Intl0042,58300011,1861117Cherry Capital0063,90900001118Bethel00000067,3331119Rickenbacker Intl0071,919037,782001120Rapid City Regional000006,48401121Theodore Francis Green State00160,53200001123James M Cox Dayton Intl00174,91200001124Des Moines Intl00340,660139,0330001126Minneapolis /St Paul Intl/Wold -Chamberlain001,273,01982,6670001128Charlotte/Douglas Intl00109,356000149,8831129Bradley Intl00443,282223,1500016,7481136General Mitchell Intl001,275,0380127,400001137Dallas Love Field0021800001138Detroit Metropolitan Wayne County001,851,13800001139Philadelphia Intl00000809,8290111Technical Development Document for EffluentLimitation Guidelines and Standards for the Airport Deicing CategorySection 9 – Pollutant Loadings andPollutant Load Reduction EstimatesTable 9-6 (Continued)AirportIDAirport NameEG-BasedFluidsGranularPotassiumAcetatePotassiumAcetateSodiumAcetateSodiumFormatePG-BasedFluidsUrea1140Memphis Intl00496,69974,3250001141Ronald Reagan Washington National00319,34734,0000078,0001142Washington Dulles Intl002,430,542619,8680001144Central Wisconsin1,858059,419000123,4401145Newark Liberty Intl002,657,0406,1430001146Northwest Arkansas Regional243,7230000018,0001147Raleigh - Durham Intl00000063,3331148Kansas City Intl00597,4654,5730001149Fort Worth Alliance005,24100001150Greater Rockford00311,914000680,2671151Kalamazoo/Battle Creek Intl0004,0000001153Akron - Canton Regional0020,0731620021,333Source: Airport Deicing Loadings Database (USEPA, 2010).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates 

### 9 .3.2 Calculate the Amount of Pollutant Load Associated with the Applied Chemical

As airfield deicing chemicals break down in th e environment, they (like aircraft deicers) result in increased COD and BOD discharges. EPA calculated the amount of COD associated with the degradation of the applied pavement deicing chemicals. Because pavement deicers containing urea will also break down into ammoni a, EPA also calculated the amount of ammonia associated with the degradation of these deicers.

As with the aircraft deicers, EPA determin ed it would not be suitable to use empirical data to estimate loadings a nd decided to calculate loadings based on standard chemical information and stoichiometric equations.

Determine the ThOD of Each Chemical

As with aircraft deicers, the ThOD estimat e was based on the molecular formula of the chemical and the stoichiometric equation of th e breakdown of the chemical to the end products of carbon dioxide and water. Table 9-7 lists the calculated ThOD for each chemical in airfield deicer.

Table 9-7. ThOD Calculations for Airfield Deicing Chemicals

Deicing Compound Molecular Formula Stoichiometric Formula ThOD (Moles of O 2 per Mole of Deicin g Compound)
EG C 2 H 6 O 2 2[C 2 H 6 O 2 ] + 5 O 2 Æ 4 CO 2 + 6 H 2 O 2.5
Urea N 2 H 4 CO N 2 H 4 CO + 4 O 2 Æ 2 HNO 3 + CO 2 + H 2 O 4.0
Potassium acetate KC 2 H 3 O 2 [C 2 H 3 O 2 ] ̄ + 1.75 O 2 Æ 2 CO 2 + 1.5 H 2 O 1.75
Sodium acetate NaC 2 H 3 O 2 [C 2 H 3 O 2 ] ̄ + 1.75 O 2 Æ 2 CO 2 + 1.5 H 2 O 1.75 Calcium magnesium acetate C 8 H 12 CaMgO 8 [C 8 H 12 O 8 ] 4  ̄ + 7 O 2 Æ 8 CO 2 + 6 H 2 O 7.0
Sodium formate NaHCO 2 2[HCO 2 ] ̄ + 0.5 O 2 Æ 2 CO 2 + H 2 O 0.25



### Determine the COD of Each Chemical

EPA next determined the COD loading associ ated with the chemical’s degradation. EPA assumed that the chemical would completely degr ade in the environment over time and therefore the calculated ThOD load would be equivalent to the COD load. EPA estimated the COD load associated with each reported chemical based on the calculated mass of the chemical purchased, the molecular weight of the chemical, the ThOD, and the molecular weight of oxygen, using the equation below:

grams 434 pound
O of moles O of grams Weight Molecular O chemical of moles O of moles ThOD chemical of grams chemical of moles Weight Molecular Chemical pound grams 434 (pounds) Chemical (pounds) Load COD

2 2 2 2 × ⎟ ⎠ ⎞ ⎜ ⎝ ⎛

× ⎟ ⎠ ⎞ ⎜ ⎝ ⎛

× ⎟ ⎟ ⎠ ⎞ ⎜ ⎜ ⎝ ⎛

× × = 

### (9-1)

112Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates 

### 9 .3.3 Estimate the Amount of Baseline Pollutant Load that is Discharged Directly

As pavement deicing chemicals are applied at a large variety of areas at an airport, the amount of pavement deicers being directly disc harged could range from close to 100 percent on pavement areas near outfall drains, to nearly 0 percent for chemicals that may fall onto grassy areas and infiltrate into the ground during a thaw . Estimating a percentage of direct discharge release of pavement deicers at a particular airport is difficult without performing a detailed study of each airport. Therefore, EPA assumed 100 per cent direct discharge of pavement deicers to represent the maximum possi ble amount of discharge.

9 .3.4 Estimate Pollutant Reductions for Each EPA Collection/Control Scenario

Urea COD Load Reduction

As described in section 9.3.2, EPA calculated the COD load associated with urea use at the surveyed airports. EPA then evaluated the amount of potassium acetate that would be required to replace the current average urea use using a comparison of application rates under varying winter conditions (see EPA’s Urea/Pota ssium Acetate memorandum (ERG, 2010) for the details of this analysis). Based on the COD load associated with the equivalent potassium acetate use, EPA determined the poten tial reductions in COD load. Table 9-8 presents by airport the COD load associated with urea use, the COD load associated with a switch to potassium acetate use, and the potential COD load reduction that would result from airfield product substitution.

Urea Ammonia Load Reduction

Because ammonia is not associated with pot assium acetate use, the amount of ammonia reduction from a urea product substitu tion is equal to the amount of ammonia associated with
urea usage.
The following equation expresses th e breakdown of urea to ammonia:

N 2 

### H 4 

### CO + H 2 

### O Æ 2 NH 3 

### + 2 H 2 

### O + CO 2



### EPA estimated the ammonia load associated with urea based on the equation above, the mass of urea use, and the molecular weights of urea and ammonia, using the equation below:

grams 434

pound
ammonia of mole ammonia grams Weight Molecular Ammonia urea of mole ammonia of moles 2 urea of grams urea of mole Weight Molecular Urea pound grams 434 (pounds) Urea (pounds) Load Ammonia

× ⎟ ⎠ ⎞ ⎜ ⎝ ⎛

× ⎟ ⎠ ⎞ ⎜ ⎝ ⎛

× ⎟ ⎟ ⎠ ⎞ ⎜ ⎜ ⎝ ⎛

× × = 

### (9-2)

Table 9-8 presents by airport the pot ential ammonia load reduction that would result from airfield produc t substitution.

113Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates

114 

### Table 9-8. Baseline Ammonia and COD Load and Potential Load Reduction Associated with the Discontinued Use of Urea as an Airf ield Deicing Chemical for In-Scope Airports

Airport ID Airport Airport Weighting

Factor Urea Load (lbs of COD) Equivalent Potassium Acetate Load (lbs of COD) Potential Load Reduction

(lbs of COD) Potential Load Reduction

(lbs of Ammonia)
1007 Yeager 2.1508 58,644 16,172 42,471 15,572
1010 Fairbanks Intl 1.0000 707,559 195,127 512,432 187,883
1012 Ted Stevens Anchorage Intl 1.0000 5,359,760 1,478,087 3,881,674 1,423,212
1017 Austin Straubel Intl 2.3269 95,606 26,366 69,240 25,387
1018 Piedmont Triad Intl 1.0000 197,491 54,463 143,028 52,441
1022 Fort Wayne Intl 1.9682 608,551 167,823 440,728 161,593
1041 Glacier Park Intl 3.1409 710 196 514 189
1043 Ralph Wien Memorial 1.0000 21,312 5,877 15,435 5,659
1053 General Edward Lawrence Logan Intl 1.0000 21,774 6,005 15,769 5,782

1066 Salt Lake City Intl 1.0000 2,389,572 658,984 1,730,588 634,519
1074 South Bend Regional 2.1417 69,136 19,066 50,070 18,358
1079 Manchester 1.0000 78,499 21,648 56,851 20,844
1090 Boise Air Terminal/Gowen Field 1.5043 575,214 158,629 416,584 152,740

1103 Juneau Intl 1.0000 1,018,715 280,936 737,779 270,506
1105 Spokane Intl 1.5192 1,061,339 292,690 768,648 281,824
1114 Stewart Intl 2.8661 323,516 89,218 234,299 85,905
1116 Reno/Tahoe Intl 1.0000 23,840 6,574 17,265 6,330
1118 Bethel 1.0000 143,501 39,574 103,927 38,105
1128 Charlotte/Douglas Intl 1.0000 319,432 88,091 231,340 84,821
1129 Bradley Intl 1.0000 35,692 9,843 25,849 9,478
1141 Ronald Reagan Washington National 1.0000 166,234 45,843 120,391 44,141

1144 Central Wisconsin 3.0156 263,076 72,550 190,526 69,856
1146 Northwest Arkansas Regional 1.8782 38,362 10,579 27,782 10,186

1147 Raleigh - Durham Intl 1.0000 134,976 37,223 97,753 35,841 Source: Airport Deicing Loadings Database. (USEPA, 2010).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 9 – Pollutant Loadings and Pollutant Load Reduction Estimates

115 

### 9.4 Ref erences

ERG. 2008a. Memorandum from Steve Strackbein (ERG) to Brian D’Amico and Eric Strassler (U.S. EPA). The Development of Snow and Freezing Precipitation (SOFP) Days and the Aircraft Deicing and Anti-icing Fluid (ADAF) Factor. (January 16). DCN AD00856.

ERG. 2008b. Memorandum from Cortney Itle (ERG) to Brian D’Amico (U.S. EPA). Airport Deicing Loadings Calculations. (April 17). DCN AD001140.

ERG. 2010. Memorandum from Steve Strackbein and Mary Willett (ERG) to Brian D’Amico and Eric Strassler (U.S. EPA). Estimated Costs for Transition to Liquid Airfield Deicing Application from Solid Airfield Deicing . (October 8). DCN AD01252.

ERG. 2011. Memorandum from Cortney Itle and Ma ry Willett (ERG) to Brian D’Amico (U.S. EPA). ADF Collection and Control Efficiency Review. (June 15). DCN AD01270.

Switzenbaum, et al. 1999. Works hop: Best Practices for Airp ort Deicing Stormwater. DCN AD00893.

USEPA. 2008. Airport Deicing Operations ADF Usage Database. U.S. Environmental Protection Agency. Washington, D.C. DCN AD001141.

USEPA. 2010. Airport Deicing Loadings Database. U.S. Environmental Protection Agency. Washington, D.C. DCN AD01257.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

116 

### 1 0. T ECHNOLOGY 

### C OSTS


### This section presents EPA’s estimates of costs for the Airport Deicing Category to implement the control and treatment technolog ies EPA considered as technology bases for existing airports in the final rule. EPA estimat ed the compliance costs for each control and treatment technology to determine potential economic impacts on the industry. EPA also weighed these costs against the pollutant load re duction benefits resulting from the control and treatment technologies.

This section discusses th e following information:

• 

### Section 10.1 – EPA’s costing approach using airport-specific data as model airports;

• 

### Section 10.2 – EPA’s methodology for estimati ng aircraft deicing costs associated with the collection and tr eatment of ADF-contaminated stormwater, including an overview of EPA’s cost model and exam ple calculations showing how the model estimates costs;

• 

### Section 10.3 – EPA’s methodology for estimati ng airfield deicing costs associated with urea substitution;

• 

### Section 10.4 – Other complia nce-related costs; and

• 

### Section 10.5 – A summary of EPA’s annualized costs evaluated for the final rule.

10.1 Cost ing Approach

The Agency used a model-site approach to estimate costs for the Airport Deicing Category. A model airport is an operating airp ort for which EPA estimated site-specific compliance costs. In general, these include sites for which EPA has questionnaire responses. EPA selected an airport-by-airport approach to estimate compliance costs based on a comparison of information from the model airports, as oppo sed to a more generali zed approach, to better characterize the current cont rol and treatment systems in place for ADF contaminated stormwater and to account for current site conditions and airport operations.

For each model airport, EPA developed both capital and operating and maintenance costs to reduce pollutant discharges from aircraft deicing and from airfield deicing. EPA combined these costs for each model airport to estimate to tal costs of each regulatory option evaluated. EPA then applied a weighting factor to the cost s for each airport to estimate national costs for each option. A description of the weighting fact ors for the Airport Deicing Category is in DCN AD01234.

EPA estimated compliance costs for the model airports using information provided in the airport questionnaire, the detailed airline questionnaire, and from individual airports and vendors. For any given model airport, the estimated costs may deviate from those that the airport would actually incur. However, EPA considers the complia nce costs to be accurate when aggregated on an industry-wide basis. These compliance costs ar e generally broken down into three categories, costs associated with aircraft deicing, costs associated with airfield deicing, and costs with documenting compliance with today’s regulation.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

117 

### 10.2 Ai rcraft Deicing Costs

This section describes the general methodol ogy for estimating costs for ADF collection and treatment, including the Airport Deicing Co st Model design and the development of cost equations that use model-airport-specific inputs. Components of the aircraft deicing costs include collection, containment and stor age, and treatment costs. EPA estimated capital and annual operating costs for each of these costing componen ts, which were then amortized to generate model-airport-specifi c annualized costs.

10.2.1 Ov erview of the ADF Collection and Tr eatment Airport Deicing Cost Model

Managing ADF-contaminated stormwater is a multistep process. EPA developed an Airport Deicing Cost Model to estimate deicing st ormwater control costs for each of these steps and the various alternatives within each step. Co sts for each selected alte rnative are combined for each airport included in the costi ng effort to develop cost estimates for the different EPA control and treatment technology options considered for the final rule. For example, regulatory costs at an airport may include a combination of alte rnatives from the colle ction, containment and storage, and treatment categories.

The EPA regulatory options were based on requiring an airport to collect and control deicing stormwater through a va riety of mechanisms. Based on information provided in the airport questionnaire and data gath ered during EPA’s engineering site visits to various airports, EPA decided to estimate costs for three collect ion technologies. Those collection technologies included GCVs alone, a combination of plug and pump system with GCVs, and use of CDPs. Each collection alternative is expected to provid e a different level of co llection efficiency for ADF-contaminated stormwater. In the final rule, EP A decided to estimate costs for only two of these technologies, GCVs and plug and pump with GCV, in part due to concerns that spaceconstrained airports may not be able to inco rporate CDP because of FAA requirements on their design and siting. EPA estimates that using only GCVs to collect ADF-contaminated stormwater from areas within the airport wh ere aircraft are deiced will colle ct 20 percent of the available ADF. Adding a plug and pump system in combina tion with GCVs to the existing stormwater drainage system is expected to coll ect 40 percent of the available ADF.

Once ADF-contaminated stormwater has been collected, the airport has a variety of alternatives for control, includi ng disposal at a POTW, off-site recycle and recovery, on-site recycle and recovery, or on-site treatment and disposal. Each of these alternatives should be considered by an airport when selecting the a ppropriate method to manage collected ADF. For the airport deicing rulemaking option analysis, EP A selected the AFB reactor treatment system as the basis of costs because of its demonstrated capability to destroy glycols and generate an effluent suitable for direct discharge. Alt hough AFB treatment systems may be more expensive to install and operate when compared to other tr eatment alternatives, EPA’s basis of all treatment conducted via AFB should provide a conservative cost estimate for i ndividual airports to treat spent ADF. For costing purposes, EPA assumed that all model airports re quiring improvement to meet the collection requirements, except for low ADF usage airports, would install an AFB system. For airports that occasionally deice ai rcraft primarily to remove frost, installing permanent collection and treatment equipment for ADF would not be practical. Instead, EPA assumes these airports would use contractors to provide deicing stor mwater collection and removal services.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

118

### EPA assumed that all airports that are required to collect additional ADF will need onsite containment or storage for the collected de icing stormwater prior to treatment in an AFB system. The final rule does not require nor is it based on collecting the full volume of wastewater generated in a deicing season. Rath er, storage is included as part of the technology basis for flow and/or pollutant equalization to support the AFB treatment system. In these cases, containment and storage selections can in clude ponds, underground storage tanks, aboveground storage tanks, or temporary storage tanks (e.g., frac tanks). EPA decided to estimate costs for aboveground storage tanks in the final rule because they will have less of an impact on subsurface utilities for which EPA does not have site-specific informati on. In addition, FAA discourages airports from installing new stormwater retenti on ponds, as they can be a lure for birds, which are a safety hazard for aircraft. Airports may also require add itional stormwater piping to transfer collected ADF-contaminated stormwater from aircra ft application areas to storage tanks.

The airport deicing cost model considers each of these alternatives to develop a costing scheme for collecting and containing ADF-contamin ated stormwater at each model airport. The Airport Deicing Cost Model also takes into account the effectiv eness of each model airport’s current control and treatment program for ADF- contaminated stormwater to determine if additional costing is requiredto comply with the regulatory options consider ed for the final rule.

In general, EPA’s approach to develop cost s for the model airports consists of the following steps:

• 

### Step 1: Develop cost equations for each collection, storage, and treatment alternative evaluated for the final rule;

• 

### Step 2 : Estimate an airport’s current le vel of ADF-contaminated stormwater collection based on information provi ded in the airport questionnaire;

• 

### Step 3: Apply the collection a nd treatment cost equations for the various components to those airports that currently collect and manage less than the control and treatment scenario percentage being evaluated to determine airportspecific capital and annual costs for th at scenario and ea ch component; and

• 

### Step 4: Estimate total airport-specific annualized costs for each component of the airport scenario for each cont rol and treatment scenario.

10.2.2 Ai rport Deicing Cost Model Equation Development

Based on the available data, EPA developed co st equations for the collection, storage, and treatment technologies that could be applied to those model airports not currently achieving the required collection percentage . In general, the Agency developed cost equations using cost data from the BAT model airports representing th eir entire system rather than attempting to estimate costs for individual components. EPA belie ves using system wide costs is a better way to estimate costs for this regulatory effort becau se all installed capital and annual operating costs are rolled under a single value, eliminating the concern th at specific components may not have been included and allowing for more robust estim ates. For example, EPA did not prepare costs for individual components within the AFB treatment system such as reaction vessels, piping, pumps, flow meters, and buildings, but instead estimated costs for the entire treatment system.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

119 

### EPA used the cost data from the model airpor ts and information supplied by equipment vendors along with airport-specific information to develo p normalized cost equations that could then be projected to other airports based on common variables. The sections below describe the development of the normalized cost equations for the collection, transf er and storage, and treatment system alterna tives evaluated by EPA.

10.2.2 .1 ADF Collection

Airports use ADF-contaminated stormwater coll ection alternatives to achieve the targeted ADF collection percentage. Collection alternatives that EPA selected for costing include developing a winter operations plan to help manage ADF use and maximize recovery of available ADF, using glycol collection vehicles to collect ADF from surfaces following aircraft deicing, and using a plug and pump system to co llect ADF. EPA estimates that airports using GCVs can collect 20 percent of the availabl e ADF, and airports using plug and pump in combination with GCVs can collect 40 percent of the available ADF. Airpor ts with deicing pads are expected to collect more than 40 percent of the available ADF and would therefore comply with the control alternatives evaluated for this final rule.

Winter Operations Plan

A large number of airports currently have a Stormwater Pollution Prevention Plan (SWPPP) that includes deicing operations duri ng the winter months. However, these SWPPPs may not provide specific guidance for achieving the regulatory requirements considered for the final deicing rule. Therefore, EPA envisions that airports wi ll supplement their SWPPP with a specific winter operations plan that includes information such as methods to verify the percentage of ADF collection, standard opera ting procedures for ADF collection technology systems, and training information for system ope rators. Once airports have assessed specific winter operations to collect a nd control deicing stormwater, they can implement a control and treatment strategy to decrease the amount of ADF leaving the airpor t through stormwater outfalls.

Costs to develop a winter ope rations plan will likely vary depending on the type of ADF collection system. EPA assumed th at airports targeting 20 percen t collection using GCVs would require 120 hours of engineering labor to prepare th e plan and those airpor ts targeting 40 percent ADF collection using a combina tion of GCVs with plug and pu mp would requireapproximately 240 hours of engineering labor. Based on an e ngineering rate of $100/ hour obtained from the airport questionnaire, the one-time costs to prepar e a winter operations plan for 20 percent and 40 percent ADF capture would be $12,000 and $24,000, respectively.

GCVs

Airports use GCVs to collect ADF-contamin ated stormwater from various locations including gate and apron areas, taxi areas, and centralized deic ing areas. GCVs can be either truck-mounted systems or tow-behind units. Drain covers that bond to surfaces to quickly seal off drains are often used in conjunction with GCVs in the area where aircraft are deiced to allow the GCVs to collect high-con centration spent deicing fluid.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

120 

### To estimate total capital costs for pur chasing GCVs and annual operating and maintenance (O&M) costs for operating GCVs, EP A used information provided by airports in the airport questionnaire.

All airports that provided co sting information, regardless of hub size, maintained three or less GCVs. EPA used the information presented in Table 10-1 to estimate the number of GCVs by airport hub size. The Agency assumes that Non-hub, Small Hub, and Medium Hub airports can operate effectively and effici ently with two GCVs and that Large Hub airports can operate effectively and efficiently with three GCVs. Additional details regarding costs for GCVs is provided in a memorandum entitled Estimated Capital and O&M Costs for Glycol Collection Vehicle Operation (ERG, 2010).

Control of drainage while operating GCVs will vary by airport. For purposes of estimating GCV costs, EPA assumed that airports use drain covers in co mbination with the GCV operation. Variables that could imp act drainage control costs include the size of drain covers and number of drains to be covered. Because these variables are airport-specific and details are not available, EPA was unable to develop a specific a pproach to estimate the cost of drain covers and the labor needed to install them. EPA has in stead incorporated a cost increase factor of 20 percent to the annual O&M cost for using GCVs . EPA assumes that a 20 percent increase in O&M costs for GCVs will cover costs to purchase and replace drain covers and labor to install and remove the drain covers as needed.121Technical Development Document for Proposed EffluentLimitation Guidelines and Standards for the Airport Deicing CategorySection 10 – Technology CostsTable 10-1. GCV Capital and O&M CostsSite IDHub SizeEstimatedADF Usage(gal/yr)Numberof GCVsTotal GCVCapital CostsCapital CostBase Year2007 GCVCapital CostTotal GCVAnnual CostAnnualCostBaseYear2007 GCVAnnualCost($/yr)UnitCapitalCost($/GCV)AnnualO&MCost($/yr)1136Medium152,9441$361,3552001$415,558$15,2682004$16,184$415,558$16,1841012Medium420,7351$273,8402001$314,916$80,0002005$82,400$314,916$82,4001113Large722,9951$250,0001997$317,500$5,0002005$5,150$317,500$5,1501066Large570,5401$353,0002004$374,180$374,1801101Medium112,0862$700,0001996$910,000$43,2362004$45,831$455,000$45,8311021Medium284,6542$530,0002001$609,500$0$304,7501036Large323,6231$283,4632006$283,463$214,5162004$227,387$283,463$227,3871065Small125,7751$325,0002005$334,750$45,0002005$46,350$334,750$46,3501031Small59,3372$518,3002001$596,045$35,0002005$36,050$298,023$36,050AVERAGE$344,238$59,773Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

122 

### Plug and pump with GCVs

Two airports provided sufficient information to estimate costs for a plug and pump type collection system. During the 2005 de icing season, the first airport used sewer balloons at eight locations, storm sewer shutoff valves at four lo cations, and two catch basi n inserts. In addition, this airport utilized two GCVs for ancillary gl ycol collection; one is a traditional truck-based GCV and the other is a GCV unit (a V-Quip Ramp Ranger) that is towed behind a tractor. The estimated capital cost for this airport’s pl ug and pump system (including the GCVs) is approximately $790,000. The plug-and-pump system operated at this airport prevents ADFcontaminated stormwater from discharging thro ugh three deicing stormw ater outfalls (USEPA, 2006a).

The second airport operates 16 plug and pump locations that prevent ADF-contaminated stormwater from leaving the airport through a maximum of five outfalls . These plug and pump operations include plugging the associated draina ge pipes and pumping out these drains with dedicated pumping trucks. According to the ai rport, the annual budget to operate the plug and pump system is approximately $1,300,000. This cost includes permit monitoring, glycol management, the pumping contractor, plus other miscellaneous costs (ERG personnel communication, May 3, 2007). Because the glycol collect ion system at this ai rport is contracted to a third party, all costs to th e airport are reoccurring annual co sts. Therefore, these O&M costs are likely over estimates compared to airports that do not contract out their glycol collection system operation.

To estimate both capital and annual O&M cost s for other airports where plug and pump collection may be applicable, EPA normalized the costs based on the number of deicing outfalls. EPA assumed that the number of deicing outfalls is related to th e number of areas where aircraft deicing occurs, so that in gene ral an airport that has a greate r number of discontiguous deicing areas will have a greater number of deicing outfalls. EPA esti mated that more deicing areas would indicate the need for additional costs a ssociated with removing ADF from those areas. Table 10-2 presents the normalized capital and annual O&M costs for the plug and pump collection system at the airports for which EPA had costing data.

Table 10-2. Normalized Capital and O&M Co sts for the Plug and Pump Collection System

Airport Deicing Outfalls Total Capital Cost (2006 $) 1 Annual O&M Cost (2006 $) Normalized Capital Cost

($/outfall) Normalized Annual O&M Cost ($/outfall) Airport 1 3 $790,000 NA $263,400 NA Airport 2 5 NA $1,300,000 NA $260,000
NA – Data not available.



### Contract Hauling of ADF-Contaminated Stormwater

For airports that occasionally deice aircra ft primarily to remove frost, installing permanent collection and treatment equipment fo r ADF-contaminated stormwater would not be practical. Instead, EPA assumes these airports w ould contract out deicing stormwater collectionTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

123 

### and removal and their costs would not vary be tween the 20 percent and 40 percent collection/ control scenarios. This costing approach impacts the following airports:

• 

### On tario International airport in California;

• 

### Bir mingham International Airport in Alabama;

• 

### Montg omery Regional airport in Alabama;

• 

### Sacra mento Mather ai rport in California;

• 

### Lovell F ield airport in Tennessee; and

• 

### Lafayet te Regional airport in Louisiana.

These airports reported that th ey do some deicing, but all repo rted or are estimated to use 5,000 gallons/year or less normalized ADF, ha d less than 100 per cent capture of ADFcontaminated stormwater, indicated that they discharged ADF-contaminated stormwater to surface waters, but reported no typical deicing m onths. Specific details regarding the costs for occasional removal of ADF-contaminated stormwat er by a local contractor is included in a memorandum entitled Estimated Annual Costs for Air ports with Limited ADF Use (ERG, 2008).

10.2 .2.2 AFB Treatment System

EPA based the proposed COD discharge lim itation on AFB treatment. As such, when applicable, EPA determined costs for in-scope fa cilities to treat collected ADF through an AFB system. EPA also included costs for a ssociated storage and transfer piping.

Transfer Piping

Piping costs to transfer collected stormwater to holding tanks prior to either on-site or off-site ADF management will vary for each airport. Variables that could impact transfer piping costs include existing subsurface utilities, soil ty pes, elevation changes, and anticipated peak precipitation events. Because each of these variab les is airport-specific and the details are not available, EPA estimated costs for each airport to construct 10,000 linear feet of new subsurface stormwater conveyance piping from various areas around the airport. EPA modified this estimate from the proposal’s 1,000 linear feet after consideri ng public comment.

Elements of a stormwater piping system in clude subsurface concrete piping, manholes and catch basins throughout the system to contro l the direction of flow. EPA obtained costs for individual elements within the system from RSMeans (RS Means, 2010) and adjusted the costs to 2006 dollars. The Agency added cost factors for pl umbing and site work to the direct costs to obtain total installed direct costs. Indirect costs for e ngineering, permits, scheduling, performance bonds, and contractor markups were added to the total installed direct costs. Table 10-3 shows the estimated installe d capital cost for 10,000 linear feet of a new stormwater conveyance piping system at an airport is approximately $1,140,000. Details regarding capital costs plus indirect cost factors are provided in a memorandum entitled Estimated Capital and O&M Costs for Addition al Stormwater Piping (ERG, 2010c).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

124 

### Table 10-3. Estimated Cost for 10,000 Li near Feet of Stormwater Piping

Description Total Cost Trenching for stormwater piping $59,000 Backfill and compact trench after piping $38,000 Concrete stormwater piping (18-inch diameter) $310,200
Manholes/catch basins $137,400
Manhole frames and covers 28,800 Plumbing (connectors, extra labor, etc.) $187,500 Site work (clearing, grading, surveying) $80,300 Engineering $67,300
Permits $16,800 Scheduling $6,700
Performance bonds $21,000 Insurance (risk, equipment floater, public liability) $19,300 Contractor markup (handling, procuring, subcontracting, change orders, etc.) $84,000 Overhead and profit $84,000 Total Installed Capital Cost for 10,000’ of Stormwater Piping $1,140,000 Source: RS Means Heavy Construction Cost Data, 64th Edition, 2010.



### Annual O&M costs for the piping and conveyanc e system include periodic inspections to verify integrity of the piping system. To estimate labor costs for TV inspection of the 18” sewer, EPA made a conservative assumption that an air port would inspect 20 percent of the storm sewer system annually (2,000 linear feet), at a rate of $1,400 per day (2006 basis). Based on engineering experience, a sewer TV crew of tw o to three persons can inspect approximately 500 feet of piping per day. At a rate of $1,400/da y, the annual airport insp ection cost would be approximately $5,600.

Storage Tanks for ADF-Contaminated Stormwater

The AFB system that forms the basis for today’s COD limitation include storage to provide both flow and concentrati on equalization. Storage tanks are used at airports to equalize either flow and/or concentration of ADF-contamin ated stormwater prior to treatment in the AFB system. The actual size of the storage tank de pends primarily on the amount of ADF-impacted stormwater generated during precipitation events , the area from which deicing stormwater is collected, and the rate the stormwater can be di scharged to the AFB. Fo r costing purposes, EPA selected aboveground rather than underground storag e tanks due to constraints such as existing underground utilities or high ground wate r levels at individual airports.

EPA obtained storage tank volumes and capital co sts when available from five airports in the airport questionnaire (USEPA , 2006b). Using normalized ADF usage data for each of these airports, EPA normalized tank volumes and costs to the annual ADF use per year to provide an equation that could be used to estimate storage tank sizes and costs at other airports. EPA’s normalized ADF usage amounts represent ADF am ounts without any water dilution. EPA chose ADF usage as the costing basis for tank storage because the amount of tank storage needed is directly related to the amount of ADF applied for aircraft deic ing, which is a function of theTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

125 

### frequency, duration, and intensity of precipitation events at a part icular airport during a deicing season. In addition, the storage ta nks at each of these airports are used to contain ADFcontaminated stormwater prior to treatment, and therefore the hydraulic capacity has likely been designed with equalization requirements (e .g., maximum flow and equalized pollutant concentrations) in mind.

The data in Table 10-4 indicate the volume of storage ta nks at the five airports ranges between 1.5 million gallons and 8 million gallon s, with the average being approximately 4.6 million gallons. The average unit cost for stor age tanks calculated from the data in Table 10-4 is $1.67/gallon. The normalized storage tank volume, calculated from the data provided in Table 10-4 , is 11.4 gal/gal ADF use/yr. The basis of the 11.4 gal/gal ADF use/yr fa ctor includes storage of ADF-contaminated stormwaters from a vari ety of collection technologies (including GCVs, diversion systems, and deicing pads) that were id entified as having glycol concentrations greater than 1 percent or in one case greater than 1,000 mg/l BOD. EPA believes that this factor will provide sufficient storage volume for those airports required to meet e ither a 20 or 40 percent available ADF collection requirement because the airports forming the basis of the factor have an ADF collection percentage greater than the considered requirement.

Table 10-4. Storage Tank Volumes and Instal led Capital Cost for Various Airports

Airport ADF Use (gal/yr) Total Storage Tank Volume (gal) Storage Tank Volume per ADF Use

(gal/gal/yr) Installed Capital Cost

(2006 $) Storage Tank Capital Cost ($/gal)

1 1,043,138 6,520,000 0.4 $795,000 1 $1.89

2 943,982 5,140,000 2.6 NA NA
3 715,836 8,000,000 11.2 $9,440,000 $1.18

4 112,086 2,000,000 17.8 NA NA
5 60,246 1,500,000 24.9 $2,890,000 $1.93

AVERAGE 11.4 $1.67
NA – Not available.
1 Cost provided for one 420,000-gallon storage tank.



### To determine if the unit cost for abov eground storage tanks was reasonable, EPA compared the $1.67/gallon unit cost to the cost for permanent storage tanks reported in the ACRP Fact Sheets (ARCP Fact Sheets). According to Fact Sheet 30, aboveground permanent storage tank costs range from $1.25 to $1.75/ga llon for tanks ranging in size from 500,000 gallons to 1 million gallons. Unit costs for stor age tanks between 1 million and 2 million gallons range from $1.00 to $1.50/gallon. Based on the data in the fact sheets, EPA believes the $1.67/gallon unit cost factor s hould provide a conservative estimate of tank costs.

The airport questionnaire res ponses provided limited data to determine the annual O&M cost for storage tanks. One airport reported a nnual O&M costs for its storage tanks ranged between $50,000 and $100,000. Using ADF usage info rmation for this airport (281,836 gal/yr) and the reported annual O&M cost for the ai rport ($75,000/yr), EPA calculated the normalized annual O&M cost for storage tanks to be $0.27 per gallon of ADF used per year ($75,000/281,836).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs 

### AFB Treatment Systems

In the proposed rule, EPA used a linear re lationship between ADF use and ADF percent collection to predict AFB costs. Public comments raised the issue that such a relationship does not consider minimum capital costs for small syst ems or the economy of scale for larger systems. All AFB treatment systems, regardless of size, will require basic components such as chemical dosing systems, gas handling systems, sludge hand ling systems, storage tanks, in-line monitoring equipment, and process control sy stems. For many of these compone nts, cost is independent of treatment system size.

To assist EPA with developing costs for AF B treatment, industry developed a cost curve that shows a general relationship between cost and COD load for systems designed to treat between 500 and 7,000 lbs/day of COD. As shown in Figure 10-1 , the cost per pound of COD removal decreases rapidly for larger load remova l systems because of the economy of scale with the reactor and separator system, and the cost fo r support buildings and facilities is relatively constant and not tied to COD loading.

y = 275101x -0.6279

0 1000 2000 3000 4000 5000 6000 7000

0 1000 2000 3000 4000 5000 6000 7000 8000
COD Loading (lbs/day )Capital Cost ($/lb COD/da



### Figure 10-1. AFB Reactor Capital Cost fo r Treating ADF-Contaminated Stormwater

Using the equation in Figure 10-1 developed from industr y comments (See Airport Council International – North America comments on EPA’s Proposed Rule for Effluent Guidelines for the Airport Deicing Category), EPA can estimate the installed capital cost for an AFB reactor (excluding storage, transfer piping, and possible land costs) if the COD loading is known. To test the accuracy of this equation, EP A compared calculated co sts to those provided by Albany International Airport (Albany) for their AFB treatment units. According to Albany airport staff, the installed cost for their AF B treatment system is approximately $8.1 million dollars (2006 $). This cost does not include equalization tanks or ponds prior to the AFB, additional stormwater piping to transfer ADF-contaminated stormwater from areas of generation to storage, or purchase of additional land to acco mmodate the AFB treatment reactors or storage. Based on Albany’s design COD loadi ng of 5,200 lbs/day, the equation in Figure 10-1 would predict an AFB installed cost of $6.6 million dolla rs (2006 $). Because the estimated cost for the Albany AFBs, using industry’s equation, is within + 20 percent of the actual cost provided by Albany, EPA concludes the equation shown in Figure 10-1 can be used to predict AFB costs for all airports.

126Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

127 

### Both the Albany and Akron-Canton (Akron) airports provided annual O&M costs for their treatment reactors. According to Al bany, its annual O&M cost is approximately $510,000/year. Akron has recently constructed its AFB and did not have actual operating data at the time of EPA’s costing analysis but did provide estimated annual O&M costs of $195,000/year (McQueen, R. and Arendt, T.). Becau se annual operating costs for an AFB system are directly related to the annual amount of ADF use and the collection percentage, EPA normalized annual AFB reactor annual ope rating costs to these two factors. Table 10-5 shows the AFB reactor annual O&M costs normalized to annual ADF usage for Albany and Akron.

Table 10-5. Normalized Annual O&M Costs for the AFB Reactors

Annual ADF Use (gal/yr) Estimated Percent Capture 1 Annual ADF Captured Annual O&M Cost (2006 $/yr) 1 Normalized Annual O&M Cost ($/gal ADF recovered) Albany 125,775 92 115,713 $510,000 $4.40
Akron 60,264 60 36,200 $195,000 $5.39
AVERAGE $4.90

1 Airport deicing loadings database.



### Land Costs

EPA has included the opportunity cost of land use for both storag e and treatment of ADF-contaminated stormwater. EPA’s approach to estimating this cost is to first estimate the amount of land needed for storage tanks and th e AFB treatment system and then apply an opportunity cost per square foot . The opportunity cost assumes the land could potentially be leased for some other use by an airport tenant if not being used for th e treatment and storage system.

To estimate the area of land associated w ith the AFB treatment system, EPA obtained information on the footprint of the AFB system s at Albany using Googl e Earth (Google Earth, 2007). Based on a review of the Google Earth imag es, EPA estimates the footprint for the AFB treatment system is approximately 2.4 acres or 104,544 sq.ft. This area would include the reactors, associated buildings, pump houses , roadways and parking areas, etc.

To predict the amount of land needed for storage tanks, EPA used the following equation developed for predicting storage tank costs:

Volume of Required Storage Capacity (gal) = ADF Use gal/yr × 13.1 gal/gal/yr

Combining this equation with the one devel oped from the figure below allows EPA to estimate the minimum footprint for storage tanks at individual airports based on ADF use. The equation shown in the figure below is based on storage tanks with a 14- foot sidewall depth.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs



### Tank Area Versus Storage Volume

y = 0.0095x - 7E-12
R 2 = 1

0 10000 20000 30000 40000 50000 60000 70000 80000 90000

0 2,000,000 4,000,000 6,000,000 8,000,000 10,000,000
Storage Capacity (gal) Area (ft2)



### Because storage tanks require a barrier-fr ee area of approximately 20 feet around the entire tank for maintenance as well as access roads to the tanks, EPA decided to increase the minimum tank footprint by 20 percent.

EPA believes that siting of AF B and deicing stormwater stor age systems will require that they be placed away from the terminal and main runway area. To estimate the value of this land if leased by an airport, EPA obtained leasing in formation from a number of airports. Based on the leasing cost data obtained from these airports , EPA selected an estimated $1.00/sq.ft. cost for purposes of the costing mode l. Additional information on land costs is included in a memorandum entitled Estimated Land Requirements and Oppor tunity Costs for the Anaerobic Fluid Bed Treatment System and ADF Stormwater Storage Tanks (ERG, 2010d).

1 0.2.3 Development of Airport Deicing Cost Model Inputs

The key inputs to EPA’s Airport Deicing Cost Model include airport operations data and site-specific precipitation and physical f eature data for the model airports.

1 0.2.3.1 Airport Operations Data

The primary source of airport operations data used in the calculation of collection and treatment costs were responses to the Agency’s 2006 airport questionnaire (U.S. EPA, 2006b). EPA entered data from all questionnaire responses in to an electronic database that it used to determine if any ADF-contaminated stormwater collection and treatm ent technologies were currently utilized and to access reported operations data needed to estimate costs for additional collection and treatment. EPA used the following specific data fr om the questionnaire responses: geographical location, aircraft de icing chemical usage, manner/frequency of deicing discharges, deicing, and ADF collection operations.

EPA required the following additional airport op erating data not requested in the airport questionnaire to estimate costs: annual ADF use and the number of annual nonpropeller aircraft

128Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

129 

### departures. EPA collected data on annual ADF usag e in its airline detail ed questionnaire (U.S. EPA 2006). EPA evaluated annual nonpr opeller aircraft departures us ing data from the Bureau of Transportation Statistics (BTS).

1 0.2.3.2 Precipitation Data and Site Characteristics

Estimating costs to collect and treat ADF-c ontaminated stormwater partially depends upon the volume of the stormwater. To predict th e annual volume of ADF-impacted stormwater generated at an airport, EPA used precipitation data along with airport s ite characteristics and assumed ADF-impacted stormwater would be co llected from areas where ADF is applied and possibly from areas where ADF may drip from the aircraft during taxi an d takeoff. EPA obtained precipitation data from 1976 to 2006 (30 year s) from NOAA for each airport questionnaire respondent and then averaged the da ta by airport to estimate an ai rport-specific monthly average. EPA uses these data, combined with the number of deicing months taken from the questionnaire responses, to estimate the averag e annual amount of precipitation that may be contaminated by ADF.

1 0.2.4 Airport Deicing Cost Model Design

This section describes how the Airport Deicing Cost Model uses the capital and annual cost equations, in combination with the model input data, to predict costs for each model airport.

10.2.4 .1 Airport Deicing Cost Model Description

EPA developed the Airport Deici ng Cost Model using Microsoft ® 

### Access. The model uses various tables structured from the airpor t questionnaire responses to provide input to the design equations. EPA designed the model to use a series of “Yes – No” statements and its assessment of the current collection efficiency achieved by an airport to build costs, as appropriate, based on the appropriate types of collection alternatives needed to achieve the target collection efficiency.

The Airport Deicing Cost Model pr ovides output costs in Microsoft ® 

### Excel for each selected collection alternative, and the trea tment system (piping, storage tanks, and AFB treatment system). The outputs include both installe d capital cost and annual O&M costs. Airport Deicing Cost Model outputs for eac h airport that is cu rrently not achieving th e analyzed percent control and treatment of ADF-contaminated stormw ater are then used to calculate annualized costs by airport. Section 10.2.5 provides more de tail regarding cost a nnualization. The Airport Deicing Cost Model collection and control cost output is $0 for those airports which EPA estimates are achieving the analyzed option for co llection and control of available ADF. EPA’s assessment of each airport’s current collection and control percentage is provided in the memorandum entitled ADF Capture and Contro l Efficiency Review (ERG, 2011).

10.2.4 .2 Summary of Airport Deicing Cost Model Equations

The Airport Deicing Cost Model uses capital and annual cost equations in combination with various input parameters to estimate costs for each option’s collection and treatment technology at each airport. Table 10-6 summarizes the cost equations used by the model, the input variables, and any assumptions used by th e model to estimate costs. The equations in TableTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

130 

### 10-6 are based on an airport collecting ADF-contaminat ed stormwater with glycol concentrations greater than 0.5 percent.

10.2.4 .1 Example Cost Calculation

The following example shows how the Airport De icing Cost Model uses the equations in Section 10.2.2 along with an airport’s questionnai re response to estimate costs. The example below is designed to more clearly illust rate the Airport Deic ing Cost Model.

Example Airport Capital and Annual Costs

Airport A has six deicing outfalls and currently has no collection or control equipment in place for ADF-contaminated stormwater. The estimate of airport normalized ADF usage is approximately 490,000 gallons per year of Type 1 and Type IV ADF. The airport has 23 deicing days per year spanning a five -month period (150 days). The ai rport does not discharge to a POTW or contract haul ADF to an off-site recovery/recycle faci lity. Based on the final rule, the airport will collect 40 percent of the available ADF using a plug and pump system with GCVs. Collected ADF contaminated stormwater will be treated by an AFB treatment system.

Winter Operations Plan Development
Engineering Labor: 240 hours × $100/hr = $24,000

Plug and pump Collection System
Plug and Pump Capital Cost: = 6 × $263,400 = $1,580,400

Plug and Pump Annual O&M Cost ($/yr) = 6 × $260,000 = $1,560,000/yrTechnical Development Document for EffluentLimitation Guidelines and Standards for the Airport Deicing CategorySection 10 – Technology Costs



### 131Table 10-6. Airport Deicing Cost Model Equations, Input Variables, and AssumptionsCalculation DescriptionEquationInput VariablesAssumptionsEstimates costs for airports toprepare a one-time winteroperations plan as a supplement tothe current SWPPP.Winter Operations Plan ($)20% ADF collection: 120 hours ×$100/hr40% ADF collection: 240 hours ×$100/hrTarget ADF collection percentageLabor costs assume airport will contractwith an outside consultant to prepare thewinter operations plan.Estimates costs to purchase andoperate GCVs to collect 20% ofavailable ADF. Includes a 20%factor on the O&M costs fordrainage control.GCV Capital Cost ($) = $344,238 ×number of GCVsGCV Annual Cost($/yr) = $59,773 ×number of GCVs × 1.2Airport hub statusSmall, medium and Non-hub airportsrequire 2 GCVs. Large Hub airportsrequire 3 GCVsEstimates costs to install andoperate a block-and pumpcollection system with GCVs tocollect 40% of available ADF.Plug and Pump Capital Cost ($) =$263,400 × outfall numberPlug and Pump Annual Cost ($/yr) =$260,000 × outfall numberNumber of stormwater deicing outfallsfrom the airport questionnaireThe number of deicing outfalls relates tothe number and size of deicing areasrequiring controls.Estimates costs to install andoperate an AFB bioreactortreatment system.AFB COD Load (lbs/day) = ADF Use× 14.28 × Collect % / 100 ×1/operating daysAFB Unit Capital Cost ($/lb/day):275,101 × (COD Load)-0.6279AFB Capital Cost ($): AFB UnitCapital Cost × COD LoadAFB Annual Cost ($/yr) = ADF Use ×Collect % / 100 × $4.90ADF use from airline detailedquestionnaireTreatment system operating periodbased on deicing months from airlinedetailed questionnaireCollection % from selected collectiontechnologyUltimate COD is 14.28 lbs COD/galType I ADF.Estimated costs to install storagetanks to equalize collected ADF -contaminated stormwater.Storage Tank Capital Cost ($) = ADFUse × 11.4 × $1.67Storage Tank Annual Cost ($/yr) =ADF Use × $0.27ADF use from airline detailedquestionnaireStorage tank volume requirement is 11.4gal per gal of ADF used per year.Technical Development Document for EffluentLimitation Guidelines and Standards for the Airport Deicing CategorySection 10 – Technology CostsTable 10-6 (Continued)

132Calculation DescriptionEquationInput VariablesAssumptionsEstimated costs to install anadditional 10,000 linear feet ofstormwater piping to convey ADFcontaminated water fromcollection to treatment.Piping Capital Cost ($) = $1,140,000Piping Annual Cost ($/yr) = $5,600NoneBased on 10,000 linear feet of 18”diameter subsurface piping.Estimated cost for land to installstorage tanks and an AFBtreatment system.AFB Treatment System Annual LandCost ($/yr) = $104,544Storage Tank Annual Land Cost ($/yr)= 1.2 × (ADF Use gal/yr × 13.1gal/gal/yr × 0.0095 ft2/gal) × $1/ft2NoneADF use from airline detailedquestionnaireAFB treatment system can be installedon 2.4 acres and the lease cost for land is$1/ft2.Lease cost for land is $1/ft2.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

133 

### AFB Biological Treatment System

AFB COD Loading = 490,000 gal/yr × 14.38 lbs COD/gal ADF × 0.4 × 1/150 days/yr = 18,789 lbs/day

AFB Unit Capital Cost ($/lb/day): 275,101 × (18,789) -0.6279 

### = $570/lb COD/day

AFB Capital Cost ($): 18,789 lbs/day COD × $570/lb COD/day = $10,711,000

AFB Annual O&M Cost ($/yr): 490,000 × 0.4 × $4.90 = $960,000/yr

Piping System

Piping system cap ital cost: $1,140,000 Piping system annual O&M cost: $5,600/yr

Storage Tank(s)
Storage Tank Capital Cost ($) = 490,000 × 11.4 × $1.67 = $9,329,000 Storage Tank Annual O&M Cost ($/yr) = 490,000 × $0.27 = $132,300

Land
AFB Cost ($/yr) = $104,544 Storage Tanks ($/yr) = $1.2 × 490,000 gal/yr × 13.1 gal/gal/yr × 0.0095 ft 2 

### /gal × $1/ft 2 

### = $60,980

The total capital and O& M costs are therefore: Cost Category Capital Costs ($) O&M Costs ($/year) Winter Operations Plan 24,000 Plug and Pump Collection System 1,580,400 1,560,000 AFB Treatment System 10,711,000 960,000 Piping 1,140,000 5,600 Storage 9,329,000 132,300 Land Opportunity Costs – For AFB Treatment System

— 104,544 Land Opportunity Costs – For Storage

— 60,980

Total 22,784,400 2,823,424



### The capital costs are then amortized and added to the annual O&M costs to assess an overall annualized cost for the facility.

1 0.2.5 Annualized Costs for ADF Collection and Treatment Alternatives

Table 10-7 presents the annualized costs by airport developed for the two control and treatment scenarios evaluated by EPA for th e final rule. See the Economic Development document (USEPA, 2012; DCN AD01280) for a more detailed analysis of annualized costs.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

134 

### Table 10-7. Annualized Costs by Model Facility for Control and Treatment 1

Airport ID Airport Current ADF Collection Annualized Cost for 20% Control and Treatment Scenario (2006 $) Annualized Cost for 40% Control and Treatment Scenario (2006 $)
1001 2 Montgomery Regional (Dannelly Field) 0 $1,168 $1,168

1003 3 Ketchikan International NA $0 $0
1004 Norfolk International 20 $0 $2,235,548
1006 Chicago O'Hare International 40 $0 $0
1007 Yeager 40 $0 $0
1008 Tucson International 20 $0 $1,069,305
1010 Fairbanks International ≥ 60 $0 $0
1011 Lambert-St Louis International ≥ 60 $0 $0
1012 Ted Stevens Anchorage International 40 $0 $0

1014 Albuquerque International Sunport 20 $0 $6,269,926
1015 Gulfport-Biloxi International ≥ 60 $0 $0
1017 Austin Straubel International 40 $0 $0
1018 Piedmont Triad International 0 $1,090,753 $8,121,534
1019 2 Ontario International 0 $1,110 $1,110
1020 Hartsfield - Jackson Atlanta International ≥ 60 $0 $0

1021 Buffalo Niagara International 40 $0 $0
1022 Fort Wayne International 0 $991,516 $3,272,310
1023* Seattle-Tacoma International 0 $1,560,687 $3,863,913
1024 Indianapolis International 40 $0 $0
1026 Dallas/Fort Worth International ≥ 60 $0 $0
1028 Denver International ≥ 60 $0 $0
1029 La Guardia 0 $2,976,443 $6,286,465
1031 Richmond International 40 $0 $0
1032 Austin-Bergstrom International 40 $0 $0
1033 Mc Carran International 40 $4,216 $4,216
1034 Metropolitan Oakland International ≥ 60 $0 $0

1035 San Diego International ≥ 60 $0 $0
1036 Baltimore-Washington International ≥ 60 $0 $0

1037 George Bush Intercontinental Airport/Houston 40 $4,099 $4,099

1040 Louis Armstrong New Orleans International ≥ 60 $0 $0

1041 Glacier Park International 0 $1,037,252 $1,266,155
1043 Ralph Wien Memorial 0 $605,365 $707,178
1044 Roanoke Regional/Woodrum Field 0 $943,332 $4,095,087
1045 2 Norman Y. Mineta San Jose International 10 $0 $0Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs


### Table 10-7 (Continued)

135 Airport ID Airport Current ADF Collection Annualized Cost for 20% Control and Treatment Scenario (2006 $) Annualized Cost for 40% Control and Treatment Scenario (2006 $)
1046 Long Island Mac Arthur ≥ 60 $0 $0
1050 Aspen-Pitkin Co/Sardy Field 40 $0 $0
1052 Wilmington International 0 $654,946 $3,131,737
1053 General Edward Lawrence Logan International 0 $4,860,377 $6,659,582

1054 Jackson Hole ≥ 60 $0 $0
1057 Will Rogers World 0 $986,385 $2,675,571
1058 Gerald R. Ford International 40 $0 $0
1059 Greater Rochester International 50 $0 $0
1061 William P Hobby ≥ 60 $0 $0
1062 2 Birmingham International 0 $2,675 $2,675
1063 Evansville Regional 0 $846,931 $1,609,927
1065 Albany International ≥ 60 $0 $0
1066 Salt Lake City International ≥ 60 $0 $0
1067 Helena Regional ≥ 60 $0 $0
1068 Eppley Airfield 0 $1,250,502 $2,132,279
1069 Cleveland-Hopkins International 40 $0 $0
1070 City of Colorado Springs Municipal 40 $0 $0

1074 South Bend Regional ≥ 60 $0 $0
1075 Pensacola Regional ≥ 60 $0 $0
1078 Nashville International ≥ 60 $0 $0
1079 Manchester 0 $1,600,420 $1,995,084
1080 Syracuse Hancock International ≥ 60 $0 $0
1081 Bob Hope ≥ 60 $0 $0
1083 Tampa International ≥ 60 $0 $0
1084 Bismarck Municipal 0 $770,509 $1,215,970
1086 Palm Beach International ≥ 60 $0 $0
1087 El Paso International ≥ 60 $0 $0
1088 Outagamie County Region al 0 $1,011,1 02 $2,412,516
1089 John F Kennedy International 0 $3,215,317 $10,136,241
1090 Boise Air Terminal/Gowen Fld ≥ 60 $0 $0
1091 Rochester International 40 $0 $0
1094 Boeing Field/King County International 40 $0 $0

1095 Chicago Midway International ≥ 60 $0 $0
1097 2 Lovell Field 0 $3,745 $3,745
1099 2 Sacramento International 20 $0 $0
1100 Toledo Express 20 $0 $1,767,861
1101 Portland International 20 $0 $2,792,934Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs


### Table 10-7 (Continued)

136 Airport ID Airport Current ADF Collection Annualized Cost for 20% Control and Treatment Scenario (2006 $) Annualized Cost for 40% Control and Treatment Scenario (2006 $)
1102 John Wayne Airport-Orange County ≥ 60 $0 $0

1103 Juneau International 0 $957,795 $2,343,519
1104 Nome 0 $618,441 $1,904,296
1105 Spokane International ≥ 60 $0 $0
1107 Pittsburgh International ≥ 60 $0 $0
1108 Louisville International-Standiford Field ≥ 60 $0 $0

1111 Port Columbus International 0 $2,029,946 $4,321,331
1113 Cincinnati/Northern Kentucky International ≥ 60 $0 $0

1114 Stewart International 40 $0 $0
1115 Jacksonville International ≥ 60 $0 $0
1116 Reno/Tahoe International 20 $0 $1,614,875
1117 Cherry Capital ≥ 60 $0 $0
1118 Bethel 0 $643,331 $1,936,511
1119 Rickenbacker International 0 $710,969 $1,433,955
1120 Rapid City Regional 0 $838,073 $4,548,952
1121 Theodore Francis Green State ≥ 60 $0 $0
1122 Southwest Florida International ≥ 60 $0 $0
1123 James M Cox Dayton International ≥ 60 $0 $0
1124 Des Moines International 40 $0 $0
1126 Minneapolis/St Paul International/Wold-Chamberlain ≥ 60 $0 $0

1128 Charlotte/Douglas International 0 $1,574,890 $2,111,996
1129 Bradley International ≥ 60 $0 $0
1130 San Antonio International 0 $780,240 $5,064,195
1131 Wilkes-Barre/Scranton International 0 $971,556 $1,476,180

1133 2 Phoenix Sky Harbor International 20 $0 $0
1135 2 Lafayette Regional 0 $1,536 $1,536
1136 General Mitchell International 44 $0 $0
1137 Dallas Love Field 40 $0 $0
1138 Detroit Metropolitan Wayne County ≥ 60 $0 $0

1139 Philadelphia International ≥ 60 $0 $0
1140 Memphis International 0 $1,740,377 $3,651,474
1141 Ronald Reagan Washington National 40 $0 $0

1142 Washington Dulles International 40 $0 $0
1143 San Francisco International ≥ 60 $0 $0Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs


### Table 10-7 (Continued)

137 Airport ID Airport Current ADF Collection Annualized Cost for 20% Control and Treatment Scenario (2006 $) Annualized Cost for 40% Control and Treatment Scenario (2006 $)
1144 Central Wisconsin 0 $952,550 $1,451,583
1145 Newark Liberty Intl 0 $5,366,144 $9,674,611
1146 Northwest Arkansas Regional 0 $873,730 $1,644,615
1147 Raleigh-Durham Intl 0 $1,294,323 $4,254,332
1148 Kansas City Intl 40 $0 $0

1 Treatment includes installation and operation of an AFB biological treatment system.
2 Airport is in a warm climate and uses either no AD F or less than 5,000 gal/yr.; EPA assumes the airport will contract out all ADF removal and disposal operations.
3 Airport was sent an airport questionnaire but did not respond. *The airport post-questionnaire has installed deicing pads. High BOD stormwater is sent to a POTW.



### 10.3 Ai rfield Deicing Costs

This section describes EPA’s co st evaluation for model airports to discontinue using urea as an airfield deicing chemical. Informati on collected by EPA during the rulemaking effort indicated that use of urea as an airfield deicing chemical is being phased out due to concerns with its environmental impacts and the availabili ty of less harmful alternatives. Responses to EPA’s airport questionnaire indicated that pota ssium acetate was by far the predominant airfield deicing chemical in use from 2002 to 2005, represen ting about 80 percent of all airfield deicing chemical use; therefore, EPA assumed that airports would switch to this chemical to deice their pavement. However, approximately 35 of the surveyed airports continued to use urea for airfield deicing during the 2002/2003, 2003/2004, and 2004/2005 deic ing seasons. EPA did not estimate capital or operating costs associat ed with airfield deicing control for model airports that did not report urea usage.

1 0.3.1 Urea and Potassium Acetate Chemical Costs and Application Rates

EPA evaluated the chemical cost of using urea compared to the chemical cost to use potassium acetate in evaluating costs for contro lling discharges associated with pavement deicing. This section presents information on th e chemical, mechanical, and storage costs to replace urea with potassium acetate. Additiona l details on urea and potassium acetate use is included in a memorandum entitled Estimated Costs for Transition to Liquid Airfield Deicing Application from Solid Airfield Deicing (ERG, 2010a).

Based on responses to the airport questionnair e (USEPA. 2006b), 19 of the airports that used urea also used potassium acetate. EPA attemp ted to contact these air ports to obtain their unit costs for both chemicals and were able to ge t unit cost data from eight of these airports. Table 10-8 presents the average cost for urea a nd potassium acetate during the 2002-2005 time frame for these eight airports.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

138 

### Table 10-8. Average Cost for Urea and Potassium Acetate, 2002-2005

Year Average Urea Cost Average Liquid Potassium Acetate Cost
2002 $268.17/ton $2.81/gallon
2003 $280.57/ton $2.86/gallon
2004 $297.90/ton $2.86/gallon
2005 $300.21/ton $2.92/gallon



### Potassium acetate is applied at different rates depending on the weather conditions and the thickness of the ice layer at the time of application. Table 10-9 shows the typical deicing, anti-icing, and prewetting application rates fo r four commercial potassium acetate runway deicers.

Table 10-9. Typical Application Rates for Potassium Acetate

Brand Name Deicing Application Rates Anti-Icing Application Rates Prewetting Application Rates Safeway® KA Runway Deicing Fluid 1 gal/1000 ft 2 0.4gal/1000ft 2 70% solid and 30% liquid

Cryotech E-36® LRD 1 gal/1000 ft 2 (thin ice) and 3 gal/1000 ft 2 (2.5cm thick ice) 0.5 gal/1000ft 2 85-95% solid and 5-15% liquid, or 130g/kg of solid deicer, 1.25gal/100lbs. solid deicer
IceClear RDF 1 gal/1000 ft 2 (thin ice) and 3 gal/1000 ft 2 (1in. thick ice) 0.5 gal/1000ft 2

PEAK® PA 1 gal/1000 ft 2 0.4 gal/1000ft 2 70% solid and 30% liquid



### Although it could not obtain actu al application rates for urea at individual airports, EPA did obtain airfield application rates for sodium acetate; therefore, the Agency used sodium acetate rates as a surrogate to estimate urea ap plication rates. The am ount of sodium acetate required to provide the same protection as urea is between 66 and 70 percent (Transport Canada, 1998). EPA used this relationship to calculate the corresponding urea application rates. Table 10-10 lists typical application rates for Cryotech NAAC®, a commercial sodium acetate deicer and the corresponding urea application rate base d on the relationship between sodium acetate and urea.

Table 10-10. Application Rates fo r Sodium Acetate and Urea

Sodium Acetate, Cryot ech NAAC®, Application Rate Urea Application Rate
Near 32°F on thin ice = 3-5 lbs/1000 ft 2 Near 32°F on thin ice = 4.3-7.1 lbs/1000 ft 2

Less than 10°F on 1 inch ice = 10-25 lbs/1000 ft 2 Less than 10°Fb on 1 inch ice = 14.3-35.7 lbs/1000 ft 2



### Using the information in Table 10-10 , EPA estimated the application costs for urea and potassium acetate based on the 2005 average un it costs ($/1,000 ft2), as shown in Table 10-11

.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

139 

### Table 10-11. Cost for Application of Urea and Potassium Acetate, per 1000 Square Feet

Chemical Deicing Application Cost (per 1000 ft 2 ) Anti-Icing Application Cost

(per 1000 ft 2 )
Urea $0.65-$1.07, Near 32°F on thin ice
Potassium Acetate $2.92 (thin ice) and $8.76 (thick ice) $1.17-$1.46



### 1 0.3.2 Mechanical Application Equipment and Storage of Potassium Acetate

Airports that change from urea to potassium acetate for airfield deicing will need new application equipment to apply a liquid rather than a solid as well as liquid storage tanks to contain potassium acetate during the deicing seas on. The following sections discuss the costs for mechanical application equipment and st orage tanks for liquid potassium acetate.

1 0.3.2.1 Mechanical Application Equipment

Airports require application equipment to spread chemical deicers on the airside pavement. A change from solid to liquid chemicals will require an airport to purchase or retrofit equipment to properly apply liquid chemical deic ers. EPA requested liquid chemical application equipment costs from vendors across the country th at offer a variety of different application equipment options and obtained costs from three vendors. EPA requested information on equipment of various sizes to assess costs by a large vs. small/medium coverage area.

Based on information provided by the vendors, EPA assumed that new trucks with a large coverage area operated w ith 100-foot spraying booms and at least 2,500 gallons of tank space. For truck retrofits or trailers, EPA assume d a large coverage area for units that operated with at least 75-foot booms and at least 2,000 gallons of tank space. EPA assumed that new trucks with a small/medium coverage area operat ed with 50-foot spraying booms and at least 1,100 gallons of tank space. For truck retrofit s or trailers, EPA assumed a small/medium coverage area for units that ope rated with booms of 50 feet or a different type of spreading mechanism. EPA used this information to estimate liquid application equipment costs for those airports that currently use solid urea.

Table 10-12 provides costing information for small/medium and large liquid deicer application equipment. Equipment is presented fo r two types of installations: new sprayer trucks and truck retrofits/towed sprayers . Costs are presented as a total capital cost and are averaged by equipment type and size.

EPA assumed that small, medium, and Non-hub airports would be re quired to purchase a medium-size spreader truck and a medium-size truc k retrofitted with a tow unit for application of potassium acetate. EPA assumed Large Hub airports would purchase a large-size spreader truck and a large-size truck retrofitted with a towed unit. Based on these equipment assumptions and the relationship between urea and potassium acetat e amounts, EPA estimated small, medium and Non-hub airports would be required to spe nd approximately $203,000 for a potassium acetate application system and large airports woul d be required to spend approximately $348,000. EPA assumed that airports using both urea and potassium acetate have sufficient applicationTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

140 

### equipment available to apply only potassium acet ate and those airports were not assigned application equipment costs.

1 0.3.2.1 Potassium Acetat e Storage Tanks

Users of liquid pavement deicers can purchase th e chemicals in various size carboys or in bulk. The actual size of bulk liqui d storage tanks needed will de pend primarily on the amount of deicing chemical purchased each deicing season . EPA used tank cost data from fact sheets contained in ARCP Report 14 (A RCP Fact Sheets) to estimate liquid pavement deicer storage costs for airports that cu rrently use solid urea for airfield deic ing and would need to convert to a non-urea-containing deicing chemical.

Table 10-12. Application Equipment Costs for Liquid Pavement Deicer

Installation Type Large Coverage Deicing Unit Medium/Small Coverage Deicing Unit
Full Truck $160,000 Tyler Ice AD Series – 4,000 Gallons with 100' Booms (Eagle) $130,000 Tyler Ice AD Series – 2,000 Gallons with 75' Booms (Eagle)

$280,000 4,000-5,000-gallon units (Tyler ICE) $197,500 2,000-3,000-gallon unit (Tyler ICE) $245,000 ASP nozzle sprayer spraying width 45 Meter. Tank content 10,000 liter (Schmidt) Average Cost 1 $228,000 $163,000

Installation Type Large Coverage Deicing Unit Medium/Small Coverage Deicing Unit
Truck Retrofit/ Spreader $110,000 3,500 2T 5M Towed Spreader (Eagle) $35,000 Smart Tote 125, 8-25' spray width (Eagle) $35,000 Epoke PC Compact , Drop behind spreader (Eagle) $130,000 Tyler Ice TAD Series, 2,000 gallons with 75' booms (Eagle) $60,000 Tyler Ice TAD Series, 500 gallons with 12-36' boomless spray (Eagle) $20,500 Small Tote Sprayer, 8-50' booms (Tyler ICE) $50,000 ASPT nozzle sprayer spraying width of 15 meters. Tank content 3,000 liters (Schmidt) Average Cost 1 $120,000 $40,000

1 – Yearly cost was calculated assuming a 6% interest rate and a 20 year loan term. Sources: Eagle – Mr. Trevor Winn, CA, CFO at Eagle Airfield (a division of Team Eagle Ltd). http://www.team-eagle.ca/

. Tyler ICE Div. of Wausau Equipment – Mr. Mark Kreutzfeldt. http://www.wausau-everest.com/ Schmidt – Mr. Rene Wender - Product Manager Airport equipment. http:// www.aebi-schmidt.com

.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

141 

### Table 10-13 provides capital costs for potassium acetate storage tanks. Costs for three types of storage tanks are presen ted: portable (frac), modular, and permanent. For smaller storage needs, EPA assumed that an airport could use th e chemical tote provided with the liquid deicer purchase. EPA assumed that O&M costs for liquid storage are about the same as those for solid storage. EPA assumes that a modular tank with a 50,000-gallon storage capacity will be the best option for airports that use between 1,000 and 50,000 gallons of liquid airfield deicing chemical each deicing season. A modular tank with a 100 ,000-gallon storage capacity will be the best option for airports that use greater than 50,000 gallons of de icing chemical each season. EPA assumed that airports using both urea and potassium acetate have sufficient liquid storage available and therefore no costs for ta nks are assigned to these airports.

Table 10-13. Storage Tank Capital Co sts for Liquid Pavement Deicer

Tank Type Size (gallon) Transaction Type Cost Cost for 2/3 of a year rental Portable (Frac) 21,000 Rental $45/day $10,980 Portable (Frac) 21,000 Rental $1,350/month $10,800 Average Portable (Frac) Tank Cost $10,890/yr Tank Type Size (gallon) Transaction Type Cost Cost per gallon
Modular 50,000 Purchase $40,000 $0.80
Modular 100,000 Purchase $50,000 $0.50
Modular 245,000 Purchase $80,000 $0.33
Modular 500,000 Purchase $130,000 $0.26
Modular 1,000,000 Purchase $225,000 $0.23
Modular 2,000,000 Purchase $375,000 $0.19 Average Modular Tank Cost $0.38 Tank Type Size (gallon) Transaction Type Average Cost Cost per gallon
Permanent 2,000,000 Purchase 2,000,000 $0.90

Permanent 4,000,000 Purchase 4,000,000 $0.70 Average Permanent Tank Cost $0.80



### The national average use of urea, based on EPA’s airport ques tionnaire (U.S. EPA, 2006b) data for the three deicing seas ons between 2002 and 2005, was 7,075,900 pounds per year. Using the available range of application rates (small coverage area and large coverage area for the same amount of urea) and statistical airp ort weighting values as determined by EPA, the Agency estimated both capital costs for equipmen t (application equipment and storage tanks) and chemical costs for a national switch from urea to potassium acetate. Table 10-14 lists the annualized capital costs for appli cation equipment and storage plus the annual cost for potassium acetate for those airports in the scope of the fina l rule that indicated they use urea. Note that airports that currently use potassium acetate for a portion of airfield deicing are assumed to have both application equipment and storage available and therefore no capital costs are required.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

142



### Table 10-14. Annualized Costs for In-Scope Airp orts to Change from Urea to Potassium Acetate for Airfield Deicing

Airport ID Annualized Capital Equipment Cost 1 ($/yr 2006) Predicted Potassium Acetate Annual Cost ($/yr 2006) Total Annualized Cost ($/yr 2006)
1007 $30,654 $10,487 $41,141
1010 $0 $150,844 $150,844
1012 $0 $657,442 $657,442
1017 $0 $16,346 $16,346
1018 $0 $38,826 $38,826
1022 $0 $105,445 $105,445
1041 $27,125 $131 $27,256
1043 $0 $3,935 $3,935
1053 $49,879 $2,243 $52,122
1066 $0 $577,406 $577,406
1074 $30,654 $12,765 $43,419
1079 $0 $8,854 $8,854
1090 $0 $159,636 $159,636
1103 $31,536 $199,901 $231,436
1105 $31,536 $251,319 $282,855

1114 $0 $59,734 $59,734
1116 $0 $2,848 $2,848
1118 $30,654 $25,971 $56,625
1128 $0 $91,667 $91,667
1129 $0 $6,590 $6,590

1141 $0 $24,660 $24,660

1144 $0 $33,209 $33,209
1146 $30,654 $10,625 $41,278
1147 $30,654 $35,153 $65,807

1 Cost includes both application equipment and storage tanks.



### 1 0.4 Other ADF-Compliance-Related Costs

In addition to the costs associated with ADF stormwater collection and control and airfield deicing chemical subs titution, EPA also analyzed po tential monitoring and reporting costs for airports to comply w ith the various options. Specifically, EPA costed the model airports
to:

• 

### Assess ADF usage (in some instances, EP A assumed that the airport would not need to assess usage);

• 

### Perform an engineering review of airport operations to determine and document compliance with the percent ADF collection standard (for those that are in scope of the analyzed collection requirements);Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

143 

### • 

### Perform annual ADF collection equipmen t/system inspections(for those who are in scope of the analyzed co llection requirements); and

• 

### Perform COD monitoring from an on-s ite treatment system (such as AFB treatment) to demonstrate compliance with the COD standards (for those facilities that are in scope of the analyzed option).

EPA’s assumptions and methodology for estim ating these costs are described below along with a summary of the in-scope airports which EPA projected would incur these costs. Table 10-15 presents these other compliance-related costs for each of the model airports determined to be in the scope of the final rule.

1 0.4.1 Assessing ADF Usage from Airport Tenants

EPA assumed that many airports using ADF dur ing typical winter seasons will need to collect and compile ADF usage information from the airlines operating at the airport. EPA is assuming that airport personnel wi ll collect ADF usage data mont hly from airport tenants and will collate that data into a spreadsheet, whic h can be totaled each seas on to assess an annual ADF usage for the entire airport. EPA is assu ming that this activity will require 8 hours per month and that ADF usage data is collected fo r 6 months of the year on average (based on airports’ reported deicing months). Costs associ ated with assessing ADF us age will therefore be:

8 hours/month × 6 deicing months/yea r × $35/hour labor rate = $1,680/year

The labor rate shown in the equation above is based on an average re ported labor rate of $33/hour obtained from responses to the airport questionnaire and an escalation rate of 7 percent to adjust costs to a 2006 basis 3 

### . EPA adjusted the labor rate so that the labor costs for the compliance activity will be on a similar-year ba sis as the other costs assessed by EPA.

EPA is assuming that only those airports th at use less than 80,000 gallons of normalized ADF per year would need to collect and assess to tal airport annual ADF. Rather than collect and tabulate ADF usage, airports that use more th an 80,000 gallons would likel y certify that their usage is above the cutoff specified in the analyzed option.

1 0.4.2 Determination of ADF Stormw ater Collection Percentage

As part of the options evaluated by EPA in th e final rule, airports with normalized ADF use of ≥ 60,000 gallons/year would need to demonstrate th at they achieve the analyzed collection requirement. Airports would meet the collecti on requirement using the technologies costed by EPA or through other means. EPA is assuming that airports would hire an engineering consultant or firm to evaluate the airport’s ADF usage data to calculate its available normalized ADF. The engineering consultant would al so evaluate information on th e airport’s pollution prevention, deicing stormwater collection, and on-site treatment or alternative disposal.

3 From Bureau of Labor Statistics, Producer Price Index industry data for the airport industry. Increase from 2004 to 2006.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

144 

### Table 10-15. Other Compliance-Related Costs by Airport

Airport ID Airport Total Annualized ComplianceRelated Costs

($/yr 2006) 1001 Montgomery Rgnl (Dannelly Field) $1,680 1003 Ketchikan Intl $1,680 1004 Norfolk Intl $1,680 1006 Chicago O'Hare Intl $9,279 1007 Yeager $1,680 1008 Tucson Intl $1,680 1010 Fairbanks Intl $9,279 1011 Lambert-St Louis Intl $9,279 1012 Ted Stevens Anchorage Intl $9,279 1014 Albuquerque Intl Sunport $21,333 1015 Gulfport-Biloxi Intl $1,680 1017 Austin Straubel International $10,959 1018 Piedmont Triad International $21,333 1019 Ontario Intl $1,680 1020 Hartsfield - Jackson Atlanta Intl $9,279 1021 Buffalo Niagara Intl $9,279 1022 Fort Wayne International $1,680 1023 Seattle-Tacoma Intl $19,653 1024 Indianapolis Intl $9,279 1026 Dallas/Fort Worth International $9,279 1028 Denver Intl $19,653 1029 La Guardia $19,653 1031 Richmond Intl $1,680 1032 Austin-Bergstrom Intl $1,680 1033 Mc Carran Intl $1,680 1034 Metropolitan Oakland Intl $1,680 1035 San Diego Intl $1,680 1036 Baltimore-Washington Intl $9,279 1037 George Bush Intercontinental Arpt/Houston $1,680 1040 Louis Armstrong New Orleans Intl $1,680 1041 Glacier Park Intl $1,680 1043 Ralph Wien Memorial $1,680 1044 Roanoke Regional/Woodrum Field $1,680 1045 Norman Y. Mineta San Jose International $1,680 1046 Long Island Mac Arthur $1,680 1050 Aspen-Pitkin Co/Sardy Field $1,680 1052 Wilmington Intl $1,680 1053 General Edward Lawrence Logan Intl $19,653 1054 Jackson Hole $1,680 1057 Will Rogers World $1,680 1058 Gerald R. Ford International $9,279 1059 Greater Rochester International $9,279 1061 William P Hobby $1,680 1062 Birmingham Intl $1,680 1063 Evansville Regional $1,680 1065 Albany Intl $19,653 1066 Salt Lake City Intl $9,279 1067 Helena Regional $1,680 1068 Eppley Airfield $19,653Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs



### Table 10-15 (Continued)

145 Airport ID Airport Total Annualized ComplianceRelated Costs

($/yr 2006) 1069 Cleveland-Hopkins Intl $9,279 1070 City of Colorado Springs Municipal 10,959 1074 South Bend Regional $1,680 1075 Pensacola Regional $1,680 1078 Nashville Intl $19,653 1079 Manchester $19,653 1080 Syracuse Hancock Intl $9,279 1081 Bob Hope $1,680 1083 Tampa Intl $1,680 1084 Bismarck Municipal $1,680 1086 Palm Beach Intl $1,680 1087 El Paso Intl $1,680 1088 Outagamie County Regional $1,680 1089 John F Kennedy Intl $19,653 1090 Boise Air Terminal/Gowen Fld $10,959 1091 Rochester International $1,680 1094 Boeing Field/King County Intl $1,680 1095 Chicago Midway Intl $9,279 1097 Lovell Field $1,680 1099 Sacramento International $1,680 1100 Toledo Express $1,680 1101 Portland Intl $19,653 1102 John Wayne Airport-Orange County $1,680 1103 Juneau Intl $1,680 1104 Nome $1,680 1105 Spokane Intl $10,959 1107 Pittsburgh International $9,279 1108 Louisville Intl-Standiford Field $9,279 1111 Port Columbus Intl $19,653 1113 Cincinnati/Northern Kentucky International $9,279 1114 Stewart Intl $1,680 1115 Jacksonville Intl $1,680 1116 Reno/Tahoe International $21,333 1117 Cherry Capital $1,680 1118 Bethel $1,680 1119 Rickenbacker International $1,680 1120 Rapid City Regional $1,680 1121 Theodore Francis Green State $9,279 1122 Southwest Florida Intl $1,680 1123 James M Cox Dayton Intl $9,279 1124 Des Moines Intl $9,279 1126 Minneapolis/St Paul Intl/Wold-Chamberlain $9,279 1128 Charlotte/Douglas Intl $19,653 1129 Bradley Intl $9,279 1130 San Antonio Intl $1,680 1131 Wilkes-Barre/Scranton Intl $1,680 1133 Phoenix Sky Harbor Intl $1,680 1135 Lafayette Regional $1,680Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs



### Table 10-15 (Continued)

146 Airport ID Airport Total Annualized ComplianceRelated Costs

($/yr 2006) 1136 General Mitchell International $9,279 1137 Dallas Love Field $1,680 1138 Detroit Metropolitan Wayne County $9,279 1139 Philadelphia Intl $9,279 1140 Memphis Intl $19,653 1141 Ronald Reagan Washington National $9,279 1142 Washington Dulles International $19,653 1143 San Francisco International $1,680 1144 Central Wisconsin $1,680 1145 Newark Liberty Intl $19,653 1146 Northwest Arkansas Regional $1,680 1147 Raleigh-Durham Intl $19,653 1148 Kansas City Intl $9,279



### EPA has estimated 264 hours and $28,424 total costs for a consulting firm to develop and document an engineering assessment using airpor t-specific data. These costs include time for project management, data analys is and evaluation of airport drawings, calculation of airportspecific ADF collection, and preparation of a re port. EPA developed the project elements and estimated the average hour ly rate for consulting engineers at $85/hour based on best professional judgment. This cost is assumed to occur once each permit cycle (i.e., once every five years). EPA assumed that all airports with ≥ 60,000 gallons/year normalized ADF usage would be required to perform this analysis of the airport’s ADF collection percent.

10.4.3 Annual ADF Collection Equipment/System Inspections

As part of the options evaluated by EPA fo r the final rule, airports could document annual compliance with the collec tion standard by demonstrating th at their selected BAT system was properly maintained and opera ted. Airports could demonstrate that they were using those technologies properly by annually inspecting the collection equi pment and documenting that the equipment was being maintained and used per the manufacturer’s specifications.

EPA assumed that an annual in spection of ADF stormwater collection equipment/systems would occur prior to the airport’s deicing s eason and would include the following types of activities as applicable:

• 

### Inspection of GCVs to ensure that they are maintained and ready for use as well as any inspection of the vehicle vacuum system recommended by the manufacturer (e.g., inspection of the v acuum pressure and/or nozzles); and

• 

### Inspection of the plug and pump or draina ge diversion system to ensure that system components are in good condition and working order (e.g., inspection and exercising of shut-off values, in spection of balloon inserts).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

147 

### EPA assumed that 2 weeks of labor (80 hours total) would be required to perform these activities on an annual basis:

80 hours/season × $35/hour labor rate = $2,800/year

EPA included these costs for all airports with ≥ 60,000 gallons/year normalized ADF usage when evaluating the options with a collection standard in the final rule.

1 0.4.4 COD Monitoring of On-Site Treatment Systems

For this costing effort, EPA assumed that airports requiring additional ADF stormwater collection and control to comply with the analyzed options , would treat the stormwater through an on-site AFB treatment system. In addition, ai rports that were alr eady achieving compliance with the collection standard that use on-site treat ment prior to direct discharge would need to monitor compliance with the COD limitation. Most of the airports that currently collect ADFcontaminated stormwater send it to a POTW or to off-site glycol recovery. However, for the costing effort, EPA did not assume either POTW discharge or transfer to an off-site glycol recovery facility would be a vi able option for those airports requiring additional collection and control. In assessing national costs, EPA assumed that airports requiring additional collection and control would need to conduct ongoing monitori ng of the effluent discharge point of the onsite treatment system to ensure permit compliance.

To estimate AFB discharge monitoring costs, EPA assumed the following:

• 

### Airports would collect a daily 24-hour composite sample of treatment system effluent for analysis of COD for each day the treatment system is operating;

• 

### Treatment systems would be operated continuously for 26 weeks per year (6 months);

• 

### Appr oximately 1 hour of labor is associat ed with sample collection and delivery of the sample to the laboratory;

• 

### Labo r costs for sample collection are $35/hr; 4 and

• 

### Cost for COD analysis by the laboratory is $22/sample 5 and includes the cost of the sample container.

Using the assumptions above, EPA calculated th e annual cost for monitoring the effluent from an airport treatment system to be $10,374/year as follows:

• 

### Samp le Analysis Cost ($/yr): 1 sa mple/day × 7 days/wk × 26 wks/yr × $22/sample = $4,004;

• 

### Labor Cost ($/yr): 1 hr/day × 7 da ys/wk × 26 wks/yr × $35/hr = $6,370; and

• 

### Total Cost ($/yr): $4,004 + $6,370 = $10,374

EPA assumed that all model air ports with normalized ADF use ≥ 60,000 gallons/year, costed for additional collection and on-site tr eatment of ADF stormwater would monitor for COD at the effluent discharge point from th e on-site treatment system. In addition, EPA

4 Average labor costs from the airport qu estionnaire escalated to 2006 year basis.

5 Sample analysis costs obtained from EPA for analysis of COD samples by contract laboratory.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

148 

### evaluated all of the other mode l airports estimated as having ≥ 60,000 gallons/year normalized ADF usage to determine which of those airports treat ADF stormwater on site and discharge the effluent directly to U.S. surface waters. As a re sult, EPA also evaluated monitoring costs for the following airports:

• 

### Washington Dulles International Airport;

• 

### Denve r International Airport;

• 

### Alb any International Airport; and

• 

### Nas hville International Airport.

EPA assumed that all of the other model air ports that would be required to meet the collection standard do not dir ectly discharge the availabl e ADF required for collection.

10.5 Summary of Annualized Costs

Table 10-16 summarizes EPA’s annualized costs fo r ADF collection and treatment, other compliance-related costs, and urea substitution costs.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

149 

### Table 10-16. Summary of EPA’s Annualized Costs for ADF Collection and Treatment, Airfield Deicing Urea Substitution, and Other Compliance-Related Costs

Airport ID Airport Airport Weighting

Factor Annualized Cost for 20% Control and Treatment

Scenario (2006 $) Annualized Cost for 40% Control and Treatment

Scenario (2006 $) Total AnnualizedADFComplianceRelated Costs

($/yr 2006) Urea Substitution Total Annualized Cost ($/yr 2006)
1001 1 Montgomery Regional (Dannelly Field) 6.7013 $1,168 $1,168 $1,680 $0

1003 2 Ketchikan International 1.0000 NC NC $1,680 $0
1004 Norfolk International 1.0000 $0 $2,235,548 $1,680 $0
1006 Chicago O'Hare International 1.0000 $0 $0 $9,279 $0

1007 Yeager 2.1508 $0 $0 $1,680 $41,141
1008 Tucson International 2.9997 $0 $1,069,305 $1,680 $0
1010 Fairbanks International 1.0000 $0 $0 $9,279 $150,844
1011 Lambert-St Louis International 1.0000 $0 $0 $9,279 $0

1012 Ted Stevens Anchorage International 1.0000 $0 $0 $9,279 $657,442

1014 Albuquerque International Sunport 1.0000 $0 $6,269,926 $21,333 $0

1015 Gulfport-Biloxi International 5.8413 $0 $0 $1,680 $0
1017 Austin Straubel International 2.3269 $0 $0 $10,959 $16,346
1018 Piedmont Triad International 1.0000 $1,090,753 $8,121,534 $21,333 $38,826
1019 1 Ontario International 1.0000 $1,110 $1,110 $1,680 $0
1020 Hartsfield - Jackson Atlanta International 1.0000 $0 $0 $9,279 $0

1021 Buffalo Niagara International 1.0000 $0 $0 $9,279 $0

1022 Fort Wayne International 1.9682 $991,516 $3,272,310 $1,680 $105,445
1023 Seattle-Tacoma International 1.0000 $1,560,687 $3,863,913 $19,653 $0
1024 Indianapolis International 1.0000 $0 $0 $9,279 $0
1026 Dallas/Fort Worth International 1.0000 $0 $0 $9,279 $0

1028 Denver International 1.0000 $0 $0 $19,653 $0
1029 La Guardia 1.0000 $2,976,443 $6,286,465 $19,653 $0
1031 Richmond International 1.0000 $0 $0 $1,680 $0
1032 Austin-Bergstrom International 1.0000 $0 $0 $1,680 $0

1033 Mc Carran International 1.0000 $4,216 $4,216 $1,680 $0
1034 Metropolitan Oakland International 1.0000 NC NC $1,680 $0

1035 San Diego International 1.0000 NC NC $1,680 $0
1036 Baltimore-Washington International 1.0000 $0 $0 $9,279 $0Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs


### Table 10-16 (Continued)

150 Airport ID Airport Airport Weighting

Factor Annualized Cost for 20% Control and Treatment

Scenario (2006 $) Annualized Cost for 40% Control and Treatment

Scenario (2006 $) Total AnnualizedADFComplianceRelated Costs

($/yr 2006) Urea Substitution Total Annualized Cost ($/yr 2006)
1037 George Bush Intercontinental Airport/Houston 1.0000 $4,099 $4,099 $1,680 $0

1040 Louis Armstrong New Orleans International 1.0000 NC NC $1,680 $0

1041 Glacier Park International 3.1409 $1,037,252 $1,266,155 $1,680 $27,256
1043 Ralph Wien Memorial 1.0000 $605,365 $707,178 $1,680 $3,935
1044 Roanoke Regional/Woodrum Field 2.1921 $943,332 $4,095,087 $1,680 $0

1045 1 Norman Y. Mineta San Jose International 1.0000 NC NC $1,680 $0

1046 Long Island Mac Arthur 1.9985 $0 $0 $1,680 $0
1050 Aspen-Pitkin Co/Sardy Field 4.7500 $0 $0 $1,680 $0
1052 Wilmington International 6.0388 $654,946 $3,131,737 $1,680 $0
1053 General Edward Lawrence Logan International 1.0000 $4,860,377 $6,659,582 $19,653 $52,122

1054 Jackson Hole 4.3500 $0 $0 $1,680 $0
1057 Will Rogers World 1.0000 $986,385 $2,675,571 $1,680 $0
1058 Gerald R. Ford International 1.5862 $0 $0 $9,279 $0
1059 Greater Rochester International 1.0000 $0 $0 $9,279 $0

1061 William P Hobby 1.0000 $0 $0 $1,680 $0
1062 1 Birmingham International 2.8410 $2,675 $2,675 $1,680 $0
1063 Evansville Regional 5.1042 $846,931 $1,609,927 $1,680 $0
1065 Albany International 1.0000 $0 $0 $19,653 $0
1066 Salt Lake City International 1.0000 $0 $0 $9,279 $577,406
1067 Helena Regional 4.2000 $0 $0 $1,680 $0
1068 Eppley Airfield 1.0000 $1,250,502 $2,132,279 $19,653 $0
1069 Cleveland-Hopkins International 1.0000 $0 $0 $9,279 $0

1070 City of Colorado Springs Municipal 1.7414 $0 $0 10,959 $0

1074 South Bend Regional 2.1417 $0 $0 $1,680 $43,419
1075 Pensacola Regional 3.9341 $0 $0 $1,680 $0
1078 Nashville International 1.0000 $0 $0 $19,653 $0
1079 Manchester 1.0000 $1,600,420 $1,995,084 $19,653 $8,854
1080 Syracuse Hancock International 1.0000 $0 $0 $9,279 $0

1081 Bob Hope 1.0000 NC NC $1,680 $0
1083 Tampa International 1.0000 NC NC $1,680 $0Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs


### Table 10-16 (Continued)

151 Airport ID Airport Airport Weighting

Factor Annualized Cost for 20% Control and Treatment

Scenario (2006 $) Annualized Cost for 40% Control and Treatment

Scenario (2006 $) Total AnnualizedADFComplianceRelated Costs

($/yr 2006) Urea Substitution Total Annualized Cost ($/yr 2006)
1084 Bismarck Municipal 3.8679 $770,509 $1,215,970 $1,680 $0
1086 Palm Beach International 1.0000 $0 $0 $1,680 $0
1087 El Paso International 3.0457 $0 $0 $1,680 $0
1088 Outagamie County Regional 2.4 841 $1,011,102 $2, 412,516 $1,680 $0
1089 John F Kennedy International 1.0000 $3,215,317 $10,136,241 $19,653 $0

1090 Boise Air Terminal/Gowen Fld 1.5043 $0 $0 $10,959 $159,636

1091 Rochester International 3.1749 $0 $0 $1,680 $0
1094 Boeing Field/King County International 5.8985 $0 $0 $1,680 $0

1095 Chicago Midway International 1.0000 $0 $0 $9,279 $0

1097 1 Lovell Field 4.9996 $3,745 $3,745 $1,680 $0
1099 1 Sacramento International 1.0000 NC NC $1,680 $0
1100 Toledo Express 2.0917 $0 $1,767,861 $1,680 $0
1101 Portland International 1.0000 $0 $2,792,934 $19,653 $0
1102 John Wayne Airport-Orange County 1.0000 NC NC $1,680 $0

1103 Juneau International 1.0000 $957,795 $2,343,519 $1,680 $231,436
1104 Nome 1.0000 $618,441 $1,904,296 $1,680 $0
1105 Spokane International 1.5192 $0 $0 $10,959 $282,855
1107 Pittsburgh International 1.0000 $0 $0 $9,279 $0
1108 Louisville InternationalStandiford Field 1.0000 $0 $0 $9,279 $0

1111 Port Columbus International 1.0000 $2,029,946 $4,321,331 $19,653 $0
1113 Cincinnati/Northern Kentucky International 1.0000 $0 $0 $9,279 $0

1114 Stewart International 2.8661 $0 $0 $1,680 $59,734
1115 Jacksonville International 1.0000 $0 $0 $1,680 $0
1116 Reno/Tahoe International 1.0000 $0 $1,614,875 $21,333 $2,848
1117 Cherry Capital 3.5400 $0 $0 $1,680 $0
1118 Bethel 1.0000 $643,331 $1,936,511 $1,680 $56,625
1119 Rickenbacker International 4.3659 $710,969 $1,433,955 $1,680 $0
1120 Rapid City Regional 3.1082 $838,073 $4,548,952 $1,680 $0
1121 Theodore Francis Green State 1.0000 $0 $0 $9,279 $0

1122 Southwest Florida International 1.0000 $0 $0 $1,680 $0Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs


### Table 10-16 (Continued)

152 Airport ID Airport Airport Weighting

Factor Annualized Cost for 20% Control and Treatment

Scenario (2006 $) Annualized Cost for 40% Control and Treatment

Scenario (2006 $) Total AnnualizedADFComplianceRelated Costs

($/yr 2006) Urea Substitution Total Annualized Cost ($/yr 2006)
1123 James M Cox Dayton International 1.0000 $0 $0 $9,279 $0

1124 Des Moines International 1.6211 $0 $0 $9,279 $0
1126 Minneapolis/St PaulInternational/WoldChamberlain 1.0000 $0 $0 $9,279 $0

1128 Charlotte/Douglas International 1.0000 $1,574,890 $2,111,996 $19,653 $91,667

1129 Bradley International 1.0000 $0 $0 $9,279 $6,590
1130 San Antonio International 1.0000 $780,240 $5,064,195 $1,680 $0
1131 Wilkes-Barre/Scranton International 2.6815 $971,556 $1,476,180 $1,680 $0

1133 1 Phoenix Sky Harbor International 1.0000 NC NC $1,680 $0

1135 1 Lafayette Regional 6.6425 $1,536 $1,536 $1,680 $0
1136 General Mitchell International 1.0000 $0 $0 $9,279 $0

1137 Dallas Love Field 1.0000 $0 $0 $1,680 $0
1138 Detroit Metropolitan Wayne County 1.0000 $0 $0 $9,279 $0

1139 Philadelphia International 1.0000 $0 $0 $9,279 $0
1140 Memphis International 1.0000 $1,740,377 $3,651,474 $19,653 $0
1141 Ronald Reagan Washington National 1.0000 $0 $0 $9,279 $24,660

1142 Washington Dulles International 1.0000 $0 $0 $19,653 $0

1143 San Francisco International 1.0000 $0 $0 $1,680 $0
1144 Central Wisconsin 3.0156 $952,550 $1,451,583 $1,680 $33,209
1145 Newark Liberty Intl 1.0000 $5,366,144 $9,674,611 $19,653 $0
1146 Northwest Arkansas Regional 1.8782 $873,730 $1,644,615 $1,680 $41,278

1147 Raleigh-Durham Intl 1.0000 $1,294,323 $4,254,332 $19,653 $65,807
1148 Kansas City Intl 1.0000 $0 $0 $9,279 $0 NC – Not Calculated.
1 Airport is in a warm climate and uses either no ADF or small amounts of ADF, and EPA assumes the airport will contract out all ADF removal and disposal operations.
2 Airport was sent an airport qu estionnaire but did not respond.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

153 

### 10.6 References

ACRP Fact Sheets, ACRP Report 14, Deicing Practices, Transportation Research Board, Sponsored to Federal Aviation Administration.

Airport Council International – North Amer ica Comments on EPA’s Proposed Effluent Limitations Guidelines and New Source Perfor mance Standards for the Airline Industry.

ERG. 2006. Memorandum from Lou Nadeau and Ca l Franz (ERG) to Marla Smith (U.S. EPA). Results of Airport Survey Sample Draw . (March 17). DCN AD01234.

ERG. 2007a. Personnel communication (email) between Mary Willett (ERG) and Roy Fuhrmann, Minneapolis/St. Paul Intern ational Airport. (May 3). DCN AD00872.

ERG. 2007b. Personnel communication (email) betw een Mary Willett (ERG) and Mark Sober, Albany International Airport. (May 3). DCN AD00865.

ERG. 2007c. Personnel communication (email) betw een Mary Willett (ERG) and Mark Sober, Albany International Airport. (June 27). DCN AD00866.

ERG. 2007d. Personnel communication (email) be tween Mary Willett (ERG) and Akron-Canton International Airport. (May 3). DCNs AD00863 and AD00864.

ERG. 2008. Memorandum from Cortney Itle a nd Robyn Reid (ERG) to Airport Deicing Administrative Record. Estimated Annual Costs for air ports with Limited ADF Use . (February). DCN AD01261.

ERG. 2010. Memorandum from Steve Strackbein and Mary Willett (ERG) to Airport Deicing Administrative Record. Estimated Capital and Operation and Maintenance Costs for Glycol Collection Vehichle Operation . (October 8). DCN AD01249.

ERG. 2010a. Memorandum from Steve Strackbein and Mary Willett (ERG) to Brian D’Amico and Eric Strassler (U.S. EPA). Estimated Costs for Transition to Liquid Airfield Deicing Application from Solid Airfield Deicing . (October 8). DCN AD01252.

ERG. 2010b. Memorandum from Mary Willett (E RG) to the Airport Deicing Administrative Record. Estimated Compliance-Related Costs for the Final Airport Deicing Rulemaking

. (November 17). DCN AD001255.

ERG. 2010c. Memorandum from Mark Briggs (E RG) to the Airport Deicing Administrative Record. Estimated Capital and O&M Costs for Additional Stormwater Piping . (July 26). DCN AD01253.

ERG. 2010d. Memorandum from Mark Briggs and Mary Willett (ERG) to Airport Deicing Administrative Record. Estimated Land Requirements and Oppor tunity Costs for the Anaerobic Fluid Bed Treatment System and ADF Stormwater Storage Tanks . (October). DCN AD01251.

ERG. 2011. Memorandum from Cortney Itle and Ma ry Willett (ERG) to Brian D’Amico (U.S. EPA). ADF Collection and Control Efficiency Review. (June 15). DCN AD01270.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 10 – Technology Costs

154 

### Google Earth Geographical Mapping System, 2007.

McQueen, R., and Arendt, T. Development of a Deicer Management Sy stem for Akron-Canton Airport.

RS Means Construction Cost Data, 68 th 

### Annual Edition, 2010.

Switzenbaum, et al. 1999. Works hop: Best Practices for Airp ort Deicing Stormwater. DCN AD00893.

Transport Canada, Transportation Development Center. “Laboratory Tes ting of Tire Friction Under Winter Condition s (TP 13392E).” May 1998.

USEPA. 2006a. Final Engineering Site Visit Report for General Mitchell International Airport, Milwaukee, WI. U.S. Environmental Protection Agen cy. Washington, D.C. (June 7) DCN AD00772.

USEPA. 2006b. Airport Deicing Questionnaire. U.S. Environmental Protection Agency. Washington, D.C. DCN AD00354.

USEPA. 2006c. Final Sampling Episode Report fo r Albany International Airport. U.S. Environmental Protection Agency. Wa shington, D.C. (July 19). DCN AD00842.

USEPA. 2010. Airport Deicing Costing Database . U.S. Environmental Protection Agency. Washington, D.C. DCN AD01256.

USEPA. 2012. Economic Analysis for Final Effluent Limitation Guidelines and Standards for the Airport Deicing Category. EPA-821-R-12-004. (March). DCN AD01280.

U.S. Department of Commerce. National O ceanic and Atmospheric Administration (NOAA) National Climate Data Center.

U.S. Federal Aviation Administration (FAA) National Fli ght Data Center.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 11 – Regulatory Options Considered And Selected For basis Of Final Regulation

155 

### 11. R EG ULATORY 

### O PTIONS 

### C ONSIDERED 

### A ND 

### S ELECTED 

### F OR BASIS 

### O F 

### F INAL 

### R EGULATION


### This section presents the technology options evaluated by EPA for the Airport Deicing Category as the basis for the final effluent limita tion guidelines and standard s. It also describes the methodology for EPA’s selection of the final technology options. Speci fically, this section describes the basis for BAT and NSPS; as detailed in this section, EPA is not establishing BPT, BCT, PSES or PSNS at this time.

The regulatory option selected provides the technology basis of the final effluent limitation guidelines and standards (ELGs). Entitie s subject to these regulations would not be required to use the specific technologies selected by EPA to establish the ELGs. Rather, an entity could choose to use any combination of operatio nal changes, pollution pr evention, and treatment technologies to comply with the limitations and st andards, provided the li mitations and standards are achieved.

11.1 BP T and BCT

EPA considered whether in this rule it was necessary to establish BPT limits, given that pavement deicers will be controlled at the BAT level. The Agency conc luded that it is not necessary to promulgate BPT effluent limitati on guidelines for the Airport Deicing Category, given that the BAT collection and treatment requirements would be at least as stringent as BPT requirements. Similarly, EPA is not establishing BCT limitations for this industry because the same wastestream that would be controll ed by BCT is being controlled by BAT.

11.2 BAT

For airfield deicing (runways), EPA conclude s that the “best available technology” for reducing ammonia in wastewater di scharges from airfields consists of using deicing products not containing urea, instead of those that contain urea. The administrative record for this rulemaking shows that products without urea ar e widely available in the industr y, and in fact are already in use at a majority of airports across the country. In addition, usi ng only deicers without urea is economically achievable by the i ndustry, as explained in the discussion of EPA’s economics analysis below.

To comply with this limitation, a discharger subject to the rule must either certify annually that it does not use airf ield deicing products that cont ain urea or airfield pavement discharges must achieve a numeric limitati on for ammonia as n itrogen of 14.7 mg/L. Table 11-1 presents the in-scope airports impacted by EP A’s BAT standards and EPA’s estimates of costs and loading removals associ ated with the final rule.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 11 – Regulatory Options Considered And Selected For basis Of Final Regulation

156 

### Table 11-1. Final Rule BAT Annualized Costs and Load Removals for In-Scope Airports

Airport ID Airport Airport Weighting

Factor Urea Substitution Total Annualized Cost ($/yr 2006) Potential Load Reduction (lbs of COD) Potential Load Reduction

(lbs of Ammonia)
1007 Yeager 2.1508 $41,141 42,471 15,572
1010 Fairbanks Intl 1.0000 $150,844 512,432 187,883
1012 Ted Stevens Anchorage Intl 1.0000 $657,442 3,881,674 1,423,212
1017 Austin Straubel Intl 2.3269 $16,346 69,240 25,387
1018 Piedmont Triad Intl 1.0000 $38,826 143,028 52,441
1022 Fort Wayne Intl 1.9682 $105,445 440,728 161,593
1041 Glacier Park Intl 3.1409 $27,256 514 189
1043 Ralph Wien Memorial 1.0000 $3,935 15,435 5,659
1053 General Edward Lawrence Logan Intl 1.0000 $52,122 15,769 5,782

1066 Salt Lake City Intl 1.0000 $577,406 1,730,588 634,519
1074 South Bend Regional 2.1417 $43,419 50,070 18,358
1079 Manchester 1.0000 $8,854 56,851 20,844
1090 Boise Air Terminal/Gowen Field 1.5043 $159,636 416,584 152,740
1103 Juneau Intl 1.0000 $231,436 737,779 270,506
1105 Spokane Intl 1.5192 $282,855 768,648 281,824
1114 Stewart Intl 2.8661 $59,734 234,299 85,905
1116 Reno/Tahoe Intl 1.0000 $2,848 17,265 6,330
1118 Bethel 1.0000 $56,625 103,927 38,105
1128 Charlotte/Douglas Intl 1.0000 $91,667 231,340 84,821
1129 Bradley Intl 1.0000 $6,590 25,849 9,478
1141 Ronald Reagan Washington National 1.0000 $24,660 120,391 44,141

1144 Central Wisconsin 3.0156 $33,209 190,526 69,856
1146 Northwest Arkansas Regional 1.8782 $41,278 27,782 10,186
1147 Raleigh - Durham Intl 1.0000 $65,807 97,753 35,841 Source: Airport Deicing Loadings Database (EPA, 2010).



### 11.2 .1 Airfield Deicing: Product Substitution of Pavement Deicers Containing Urea

In general, airports discharg e airfield pavement deicing ch emicals without treatment, due to the difficulty and expense of collecting a nd treating the large volumes of contaminated stormwater generated on paved airfield surfaces. EPA is not aware of an available means to control these pollutants by collecting and using a conventional, end-of-pipe treatment system. It is possible, however, to reduce or eliminate cer tain pollutants by modifying deicing practices, such as using alternative chemical deicing produc ts. In particular, EPA has identified ammonia and COD from airfield deicing as pollutants of concern, and bot h of these pollu tants are a byproduct of pavement deicers containing urea. Ac cordingly, to address di scharges of ammonia from airfield pavement, EPA identified one ca ndidate for best available technology: product substitution, or discontinuing th e use of pavement deicers cont aining urea and using alternativeTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 11 – Regulatory Options Considered And Selected For basis Of Final Regulation

157 

### pavement deicers instead. EPA f ound that using deicers withou t urea is the best available technology for reducing discharges of ammonia from pavement deicing because it is safe, technologically feasible , and available across the industry. Currently only about 10 percent of chemical pavement deicers applied nationwide c ontain urea. The most widely used pavement deicer is potassium acetate, which represents 63 pe rcent of all chemical pavement deicers applied nationwide.

11.2 .2 Aircraft Deicing: ADF Collection Requ irements and Effluent Limitations

11. 2.2.1 Available ADF Collection Technologies and Scope

EPA is not aware of an available and econom ically achievable tec hnology that is capable of capturing 100 percent of the sprayed ADF. As described above , the available technologies for collecting ADF are glycol collection vehicl es, plug and pump equipment, and CDPs. EPA estimates these technologies colle ct 20 percent, 40 percent, a nd 60 percent of available ADF, respectively.

After considering the comments provided on the proposed regulation and reviewing the information in its record, EPA is not establis hing a 60 percent ADF coll ection requirement based on CDPs for BAT. First, in response to FAA’s c oncerns about the exclusive use of deicing pads for aircraft deicing, EPA contac ted a number of Large Hub air ports that currently use CDPs. EPA found the current percentage of flights for which these airports use the CDPs ranges from 50 to 95 percent. The airports explained that va rious operational or weat her-related issues may make deicing pad use for all flights cumbersome if not impossible (i.e ., severe system-wide delays), and require them to deice at the gate in some circumstances. EPA shares the commenters’ and FAA’s concerns that moving to exclusive use of CDPs for all deicing might lead to operational issues a nd delays. EPA, in discussions with FAA, attempted to craft regulatory provisions to allow an airport limited ability to bypass the use of a centralized pad to avoid these circumstances. However, limited data on the site-specific nature of this industry left EPA unable to develop regulatory pr ovisions that would give airports the flexibility they need to avoid significant operational issues and delays. Second, based on public comments and information from FAA, EPA is concerned that some large airports critical to efficient air traffic operations in this country are space (land) cons trained and that buildi ng well-located CDPs for all deicing operations at these ai rports is likely not feasible fo r that reason. At the time of the proposal, EPA estimated that 14 airports woul d be subject to the 60 percent collection requirement. Because the data in EPA’s record indicate that many of these airports currently meet this requirement, EPA estimated approximately seven airports would likely need to install pads as a result of the proposed requirement. Of these seven airports, four are Large Hubs that, over years of expansions and other improvements, have already built out the majority of the land available to them. EPA has conc luded that the lack of remain ing available land, coupled with their existing layouts, has left these airports in a position where they cannot construct a CDP that conforms to FAA’s Advisory Circulars on deicing pad design (e.g., in a loca tion that aircraft can travel to safely and efficientl y to conduct deicing operations).

Therefore, for the final rule, EPA has not established a 60 percent ADF collection requirement, which would have been based on id entifying centralized deicing facilities as BAT for 100 percent of aircraft de partures. Because of land cons traints and the other reasonsTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 11 – Regulatory Options Considered And Selected For basis Of Final Regulation

158 

### discussed above, EPA finds that cen tralized deicing fac ilities should not be identified as BAT for this nationwide rulemaking.

EPA then considered the other two technologi es described in the proposed rule as a possible basis of BAT for aircra ft deicing discharges for th e final rule: 40 percent ADF collection requirement based on plug and pum p with GCVs and 20 percent ADF collection requirement based on GCVs. With either of these collection technologies, as was the case in the proposed rule, EPA also included numeric COD lim itations for direct discharges of collected ADF based on anaerobic treatment.

11.2 .3 Options Considered for Today’s Final Re gulation for Identification of BAT for ADF Collection and Discharge Requirements

Using the technology bases identif ied above for airfield and ai rcraft deicing discharges, EPA developed three primary options for the final rule. All three of these options have the same airfield pavement deicing discha rge requirements based on product s ubstitution of deicers that do not contain urea, but would vary the approach to control ai rcraft deicing discharges:

• 

### Optio n 1: 40 percent ADF collection require ment for large and medium ADF users (based on plug and pump with GCVs ); numeric COD limitations for direct discharges of collected ADF (based on anaerobic treatment);

• 

### Optio n 2: 40 percent ADF collection requireme nt for large ADF users (based on plug and pump with GCVs) and 20 per cent ADF collection requirement for medium ADF users (based on GCVs); numeric COD limitations for direct discharges of collected ADF (based on anaerobic treatment); and

• 

### Opt ion 3: Site-specific aircraft deicing disc harge controls: Do not establish effluent limitation guidelines in the final ru le for aircraft deicing discharges, but instead, leave the determination of BA T requirements for each airport to the discretion of the permit writer on a case -by-case, “best prof essional judgment” basis based on site-specific conditions.

Under the first option, in addition to the airfield pavement requirements, all airports that use greater than or equal to 60,000 gallons of normalized ADF annually would be required to collect 40 percent of available ADF based on plug and pump with GCV technologies. In the proposed rule, EPA considered but did not identif y this as its lead option because it found its costs to be comparable to those of CDPs, while CDPs collect more ADF. In the proposed rule, EPA therefore identified CDPs as BAT. Because EPA no longer considers CDPs to be the best available technology for existing airports, the plug and pump w ith GCV option represents the technology, among those that remain under considerat ion for the final rule, that would collect the most ADF.

Under the second option, in addition to the ai rfield pavement requirements, all airports that use greater than or e qual to 60,000 gallons of normali zed ADF annually but less than 460,000 gallons of normalized ADF (“medium ADF us ers,” estimated to be 42 airports) would be required to collect 20 percen t of available ADF based on GCVs , and airports that use more than 460,000 gallons of normalized ADF (“large ADF users,” estimated to be 14 airports) wouldTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 11 – Regulatory Options Considered And Selected For basis Of Final Regulation

159 

### be required to collect 40 percen t of available ADF based on the use of plug and pump with GCV technology.

Under both Options 1 and 2, fac ilities would need to meet numeric effluent limits for COD for the collected ADF prior to commingling it with other wastestreams prior to discharge.

Under the third option, EPA would establish national deicing discharge controls for airfield pavement deicing only. BAT limitations for aircraft deicing discha rge would continue to be established by the permitting authority on a case-by-case basis.

11.2.4 BAT Options Selection

EPA is selecting Option 3 as best availabl e technology for controlling airport deicing discharges. EPA has determined the best availabl e technology for controlling airfield pavement discharges is product substitution. The administra tive record for this rulemaking shows that products without urea are widely av ailable in the industry, and in fact are alrea dy in use at a majority of airports across the country.

With respect to aircraft deicing discharge co ntrols, EPA’s record demonstrates that ADF collection and associated treatmen t technologies are technically f easible for many airports. Data supplied from the industry through EPA’s nationally representative survey of airports indicates that dozens of airports currently use GCVs and plug and pump collection systems as well as myriad pollution prevention technologies and pr actices, ranging from alternative means of applying ADF (e.g., forced air nozzles) to alternat e deicing technologies (e .g., infrared deicing). Thus, this industry has numerous technology opt ions available for mitigating the pollutants associated with aircraft deicing activities.

However, EPA concludes that none of the ADF collection technologi es considered for the final rule represents the “best available technology” for the entire category. Rather, EPA concludes that best available technology determina tions should continue to be made on a sitespecific basis because such determinations approp riately consider local operational constraints (e.g., traffic patterns), land availability, safety co nsiderations, and potential impacts to flight schedules. Based on the information in its ad ministrative record, EP A cannot identify with precision the extent to which such limitations may preclude any part icular airports from implementing the technologies that it considered for BAT control of aircraft deicing discharges. However, the record demonstrates that such limitations exist and ar e not isolated or insignificant. More specifically, comments pr ovided by airport and airline i ndustry on the proposed regulation raised concerns about the impacts that ADF co llection technologies may have on safety and operations at airports across the country. They al so commented on the lack of available space at many land-constrained airports for ADF collectio n and treatment technologies. EPA reviewed the information submitted in comments, subsequent information provided by industry, and information obtained from site vi sits to thoroughly eval uate these concerns. After reviewing this information, EPA agrees with commenters that, wh ile many airports likely are able to implement some form of collection or pollution prevention technologies to mitigate pollutant discharges associated with aircraft deicing, other airports may not be able to implement specific technologies due to space, safety, and operationa l considerations. This became particularly apparent after reviewing questionn aire responses from some of th e airports at which EPA also conducted site visits. EPA found that its “model f acility” approach was not a suitable substituteTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 11 – Regulatory Options Considered And Selected For basis Of Final Regulation

160 

### for a detailed analysis of the site constraints at each airport. For example, a permit authority may need to evaluate existing traffic patterns at an airport, not only of the aircraft, but also of the service vehicles, to determine if additional collection vehicles w ould lead to unacceptable safety concerns. With respect to land constraints, w ithout detailed airport sc hematics or conducting a detailed site visit at each air port, EPA cannot determine if adequa te space exists to incorporate the specific treatment and colle ction technologies evaluated as the basis for the final rule.

Additionally, industry, and FAA in particular, have expres sed concerns about possible delays and economic impact that could result from using plug and pump and GCVs, both at specific airports and nationwide. EPA agrees that delays must be a factor in considering today’s possible requirements and recognizes that such de lays fundamentally affect U.S and international business and recreational interests.

Airplane deicing activities, by their nature, occur during freezing precipitation events. For some airports, even small amounts of precipitation can lead to delayed aircraft departures – even without deicing activity and/or ADF collection and treatment. As su ch, it is difficult to determine if delays at an airport during inclement weat her are associated with the weather, the ADF collection and treatment t echnologies, or both. Further, even sm all delays at certain hub airports have a ripple effect that can affect th e entire national air traffic schedule.

Some airports have identified procedures to mitigate or prevent delays associated with aircraft deicing discharge cont rols, but these approaches may not be applicable nationwide. Further, the extent of delays deemed acceptabl e is likely to vary by airport. As with land constraints, the confounding factors that need to be considered to evaluate possible delays that may be associated with the technology bases do not lend themselves to a national determination using a model facility approach. Further, EPA does not have detail ed site-specific information to evaluate delays on an airport-by-airport basis.

While the facts stated above do not preclude the ability of an airport to collect and treat spent ADF, they do illustrate why EPA did not sele ct any of the technologies considered as BAT for the final rule, and why a site-specific BAT determination for ADF collection and treatment requirements is the proper approach.

Therefore, for the reasons identified a bove, EPA determined Option 3 is the only technologically feasible and available option considered fo r today’s final BAT requirements. Option 3 would remove 4.4 million pounds of a mmonia and 12 million pounds of COD, with a projected annual cost of $3.5 million. The costs of Option 3 are reasonable in terms of the pollutant reductions achieved ($0.21/ lb). Further, as discussed in more detail in the preamble to the final rule, EPA finds Option 3 is economically achievable. In addition, EPA examined the non-water-quality impacts anticipated from co mpliance with Option 3 requirements and found none or only very minor impacts in comparison to typical industry energy use, emissions generation, and sludge generation. Therefore, base d on all the factors above, EPA is identifying Option 3 as BAT and has based today’s fina l rule on the Option 3 BAT requirements.

11.3 NS PS

For today’s final rule, EPA evaluated “best av ailable demonstrated control technologies” for purposes of setting new source performan ce standards under CWA section 306. Section 306 directs EPA to promulgate NSPS “for the control of the discharge of pollutants which reflects theTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 11 – Regulatory Options Considered And Selected For basis Of Final Regulation

161 

### greatest degree of effluent reduction which the Administrator determines to be achievable through application of the best available demonstrated control technology, processes, operating methods, or other alternatives, including, wher e practicable, a standard permitting no discharge of pollutants.” Congress envisioned that new trea tment systems could meet tighter controls than existing sources because of the opportunity to incorporate the most efficient processes and treatment systems into the facility design. As a result, NSPS should represent the most stringent controls attainable thro ugh the application of the best ava ilable demonstrated control technology for all pollutants (that is, conventional, nonc onventional, and prior ity pollutants).

After careful consideration of the informati on in its record, EPA is today promulgating the same NSPS requirements for both airfield pavement deicing discharges and airplane deicing discharges as it proposed. However, the applicability of the NSPS requirements has changed and EPA has revised the new source definition in the ru le to mean new airpor ts only and exclude new runways at existing airports. EPA determined that, just as with existing sources, all new sources would be able to substitute airfield deicing products wit hout urea for those with urea. Furthermore, product substitution represents the greatest ammonia level reduction among the available technologies considered. Accordingl y, EPA identifies product substitution of non-ureacontaining airfield deicers as the best demons trated available contro l technology for all new sources. As with BAT, there would be two alterna tives for meeting this effluent limitation: either a certification requirement or a numeric limit on ammonia for al l direct discharges of the stormwater from the airfields.

The final rule NSPS also includes a 60 per cent collection (based on CDP technology) and control requirement for ADF-contaminated stormw ater at new airports anticipated to conduct significant aircraft deicing activities. EPA, in c onsultation with FAA, finds that safety, space, and operational constraints that may be presen t at existing airports for the collection and treatment technologies discussed in the final ru le (CDPs, plug and pump with GCVs, and GCVs alone), would not apply to new airports. New ai rports can be designed to minimize space and logistical constraints identified for retrofits at existing airpor ts. Further, among the collection technologies for ADF that EPA considered, CDPs collect the greatest le vel of available ADF. Meeting the new source requirement s would not be an economic barr ier to entry for new airports, as the cost of new airport construction, even sma ll airports, is significantly greater than the costs associated with collection and/ or treatment of spent deici ng fluids (see DCN AD01260 for further detail). Moreover, according to FAA, when designed properly, CDPs often improve traffic flow and reduce delays associated with ai rcraft deicing. When designing a new airport, the local operating agency plans the site for all n eeded facilities, such as runways, taxiways, terminal(s) and other components needed to comply with safety and environmental requirements, and this includes deicing facilities. See FAA Advisory Circular 150/5070-6B, “Airport Master Plans,” and FAA Advisory Circul ar 150/5300-14B, “Design of Airc raft Deicing Facilities,” DCN AD00852. Finally, EPA notes that it did not receive any negative comments on its proposal to base the NSPS ADF collection requirement s on CDPs. See DCNs AD01260, AD01284, and AD01335for EPA’s rationale for setting NSPS applicability.

As a point of clarification, EPA is promul gating the same numeric COD limitations for collected ADF that is discharged directly from new sources as were proposed. The technology basis of the COD limitations, AFB, is available to new airportsand achieves the greatest level of pollutant removals of those tec hnologies considered during the development of this regulation.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 11 – Regulatory Options Considered And Selected For basis Of Final Regulation

162 

### Further, installing and using th is technology is not economically a barrier to entry for new airports.

11.4 PSES and PSNS

EPA is not promulgating PSES and PSNS for the Airport Deicing Category. Although some airports in the United States discharge ADF-contaminated stormwater to POTWs, EPA received no comments or other in formation indicating that POTWs currently have problems of pollutant pass-through, interferen ce, or sludge contamination st emming from these discharges that would necessitate the pr omulgation of national categoric al pretreatment standards.

Like the biological treatment system that forms the basis for today’s COD limitations, POTWs typically use biological treatment systems and are similarly designed to remove organic pollutants that contribu te to COD and/or BOD 5 

### . In general, POTWs can achieve comparable removals to the BAT technology basis. However, some airports and POTWs may need to make operational adjustments to proces s the wastewater effectively wh ile avoiding POTW upset. EPA received a comment about the Downriver Treatment Facility in Detroit, Michigan, which accepts ADF wastewater from the Detroit Metropolita n Wayne County Airport. The treatment plant experienced viscous bulking due to a nutrient imba lance that occurred dur ing the months that ADF was accepted. The issue was resolved by re moving phosphorus at a later stage in the treatment plant system, rather than from the ra w wastewater. The airpor t also made significant changes to segregate their deicing stormwater, capture and recycle the most concentrated ADFcontaminated stormwater, and control the amount a nd concentration of stor mwater discharged to the POTW.

EPA is aware that high concentration or “sl ug” discharges of de icing stormwater can create POTW upset. The national pretreatment program regulations specifically prohibit industrial users from discharging high concentrations of oxygen-demanding pollutants to POTWs if they cause interference to th e POTW (see 40 CFR 403.5(b)(4)). Under 40 CFR 403.5(c), control authorities may se t and enforce “local limits” for airport discharges to POTWs to implement the prohibitions listed in § 403.5(b)(4 ). This provision ensures that any potential limits would protect against POTW interferen ce by the oxygen-demanding pollutants in airport deicing discharges. See “Local Limits De velopment Guidance,” document no. EPA 833-R-04- 002A, July 2004, available on EPA’s website at: http://cfpub.epa.gov/ npdes/pretreatment/pstandards.cfm.

As a result, many airports that discharge to POTWs have airport-specific requirements on allowable BOD 5 

### or COD discharge loadings per day to the receiving POTWs. Airports usually meet this requirement by storing deicing stormwater in ponds or tanks and metering the discharge to meet the POTW permit loading requirements.

11.5 References

ERG. 2008. Memorandum from Cortney Itle (ERG) to Brian D’Amico (U.S. EPA). Airport Deicing Loading Calculations. (April 17). DCN AD01140.

ERG. 2012. Memorandum from Mary Willett and Cal Franz (ERG) to Brian D’Amico (U.S. EPA). NSPS Feasibility – ADF Collec tion and Treatment Requirements . (January 23). DCN AD01284.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 11 – Regulatory Options Considered And Selected For basis Of Final Regulation

163 

### USEPA. 2009. Economic Analysis for Proposed Effluent Limitation Guidelines and Standards for the Airport Deicing Category. U.S. Environmental Protection Agency. Washington, D.C. EPA 821-R-09-005. DCN AD01196.

USEPA. 2010. Airport Deicing Loadings Database. U.S. Environmental Protection Agency. Washington, D.C. DCN AD01257.

USEPA. 2012. Memorandum from Brian D’Amico (U.S. EPA) to Record. Final Rule Barrier to Entry Analysis for New Source Performance Standards for Airport Deicing . (February 8). DCN AD01260.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 12 – Non-Water Quality Impacts

164 

### 12. N ON 

### -W ATER 

### Q UALITY 

### I MPACTS


### Sections 304(b) and 306 of the CWA re quire EPA to consider non-water-quality environmental impacts (including energy requir ements) associated with effluent limitation guidelines and standards. As explained in the pr eamble to the final rule, EPA evaluated three regulatory options for today’s rule. The first tw o options are based on t echnologies to control aircraft and airfield de icing discharges

, while the the third option is base d on technology solely
to contro l airfield deicing discharges.

In considering non-water quality environmenta l impacts, EPA first analyzed the potential impact of the Option 1 technologies on energy consumption, air emissions, and solid waste generation. Because Option 2 is similar to Op tion 1, but would result in fewer operational changes at a subset of airports and therefore lead to fewer non- water quality impacts than Option 1, EPA did not analyze non-water quality imp acts associated with Option 2. Rather, EPA concluded that the results for Option 2 will be similar to or less than Option 1. Additionally, Option 3 has no associated non-water quality imp acts as substituting one airfield deicing product with another causes no increase in energy usage, air emissions, or solid waste generation.

12.1 En ergy Requirements

EPA estimated that the total incremental el ectrical usage for Option 1 to pump ADFcontaminated stormwater into storage tanks would be approximately 1.2 million kilowatt hours per year (kWh/yr). EPA also developed a relati onship between electrical use and COD removal by the AFB bioreactors based on information pr ovided by Albany Interna tional (ALB) airport. Using ALB’s information, EPA estimated the electrical requirement for COD removal for Option 1 as approximately 1.3 kWh/lb COD remove d. Using this unit rate, EPA estimated total electrical requirements to remove COD for Option 1 to be a maxi mum additional 22 million kWh/yr.

EPA also analyzed fuel use by GCVs co llecting ADF-contaminated stormwater. EPA used airport questionnaire data for diesel fuel costs for GCVs and then estimated an average diesel fuel use based on the unit cost for diesel fuel of $2.07/gal. 6 

### EPA then estimated annual fuel usage per gallon of applied ADF to be 0.08 gal/gal ADF applied. Using this relationship, EPA estimated that the total incremental consumpti on of No. 2 diesel fuel, at all airports subject to BAT and installing additional collecti on equipment, is 354,500 gallons per year.

Additionally, as EPA assumes that aircraft ope rations will not be delayed as a result of Option 1 and that deicing will occur at the gates, there is no increase in jet fuel consumption associated with Option 1.

Below are the calculations to determine the net energy requirements associated with Option 1 of the final rule for the collection a nd treatment of ADF-contaminated stormwater. Detailed calculations regarding net energy consumption for the va rious collection and treatment technologies considered for the rule are pr ovided in a separate memorandum entitled Energy Requirements for ADF Contaminated Stormw ater Collection and Tr eatment Alternatives (ERG, 2008a).

6 This diesel fuel price was the average reported by th e Energy Information Administration (EIA) for the 2004-05 winter season, the same period that EPA is analyzing for airport deicing activity.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 12 – Non-Water Quality Impacts 

### To estimate incremental electr ical requirements associated with pumping collected ADF to storage tanks, EPA assumed airports would continuously operate thr ee well-pit pumps with 40-horsepower (hp) electric motors during each deicing day. EPA also conservatively assumed that all airports would use pumps rather than a llow ADF-impacted stormwat er to flow by gravity to holding tanks. To estimate electrical use by ai rport based on the number of deicing days per year, EPA developed the following equation:

yr days SOFP day hr 24 hp kW 7456.0 pump

HP 40pumps 3 Electrical Pumping ×× ××= 

### (12-1)

Using the equation above, the total SOFP days for those airports that EPA assumed would install additional collecti on equipment, and a wire-to-wate r efficiency of approximately 40 percent (Bower, H., 1978), the to tal incremental electrical usag e to pump ADF-contaminated stormwater into storage tanks would be approximately 1.2 million kilowatt hours per year (kWh/yr).

EPA developed another relationship between electrical use and COD removal by the AFB bioreactors based on informa tion provided by Albany International (ALB) airport. Using ALB’s information, EPA estimated the elect rical requirement for COD removal as approximately 1.3 kWh/lb COD removed. Using this unit rate, EPA estimated the total electrical requirements associated with COD treatment. EPA estimates an additional 22 million kWh/yr will be required to remove 16,602,900 total pounds per ye ar of COD as a result of the final rule.

The national estimated increase in electrical power consumption related to increased pumping and AFB treatment is 23.2 million kilowatt hours per year. This represents a very small fraction (0.0006 percent), of the electrical energy used annua lly in the United States, which is 3,950 billion kWh based on EIA statistics.

EPA notes that AFB treatment systems also ge nerate biogas that can be used as a source of heat when burned in facility boilers or when converted to electricit y using technologies such as microturbines or fuel cells . EPA did not include microturbi ne costs in its option-costing methodology. However, to estimate the potential elec tricity that could be generated if all AFB treatment systems installed microturbines to ge nerate electricity, EPA developed a relationship between biogas generation and COD removal based on data provided by ALB airport. EPA estimated the AFB reactors will generate approxim ately 8 cubic feet of biogas per pound of COD removed, and the biogas is approximately 60 pe rcent methane. Because one cubic foot of methane provides 100 therms and 1 therm is equivale nt to 29.3 kWh when c onverted to electrical energy (U.S. Code, Title 15), EPA was able to predict the potential elect rical energy available from biogas generated by the AFBs treating ADF-contaminated stormwater (see Table 12-1 ).

165Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 12 – Non-Water Quality Impacts

166 

### Table 12-1. Potential Electricity Gen eration from AFB Biogas Generation

Regulatory

Scenario Total COD Removal (pounds/yr) Potential Biogas Generation (million ft 3 /yr) 1 Potential Methane Generation (million ft 3 /yr) 2 Potential Electrical Generation (million kWh/yr) 3
40% ADF Capture 16,602,900 129 77.5 23

1 Calculation based on 8 cubic feet of biogas per lb COD removed.
2 Assumes biogas is approximately 60% methane per Metc alf and Eddy Wastewater Engineering and Design (Metcalf and Eddy, 1979).
3 Calculation based on 100 therms per cubic foot of methane and 29.3 kWh per therm.



### Comparing the potential electri cal generation from converting biogas to electricity to the electrical requirements discu ssed above indicates that AFB treatment of ADF-contaminated stormwater could generate most of the electric ity needed to operate the treatment systems.

Fuel use by GCVs collecting ADF-contaminated stormwater is another incremental energy requirement for compliance with Option1. To estimate incremental diesel fuel use by GCVs, EPA obtained annual diesel fuel costs for GCVs from th e airport questionnaire (U.S. EPA, 2006) and then estimated diesel fuel use base d on the unit cost for diesel fuel (e.g., $/gal). According to questionnaire data, one airport spent $17,600 on diesel fuel to operate GCVs to recover ADF-contaminated stormwater dur ing the 2004-2005 deici ng season, collecting approximately 20 percent of thei r applied ADF in stormwater. Ba sed on an average diesel fuel cost of $2.07 per gallon during the 2004/2005 deicing season (U.S. DOE, 2006), EPA estimates this airport burned approximately 8,500 gallons of diesel fuel in GCVs. Based on annual ADF use and size, EPA estimated diesel fuel use in GCVs to be 0.08 gal/gal ADF applied. Using this relationship, EPA estimated total incremental No. 2 diesel fuel consumption at in-scope airports installing additional collection equipment to be 354,500 gallons per year. This volume is a conservative estimate because it is based on an ai rport that currently uses only GCVs to collect ADF-contaminated stormwater (e.g. , 20 percent ADF collection). If airports install a plug and pump system to collect ADF-contaminated stormw ater, GCV usage and therefore diesel fuel use are expected to be less.

EPA compared incremental diesel fuel use by GC Vs at all airports to diesel fuel use on a national basis. According to the EIA, approxima tely 25.4 million gallons per day of No. 2 diesel fuel was consumed in the United States in 2005 (U.S. DOE, 2006). Total annual diesel fuel use by GCVs to collect ADF-contaminated stormwater at airports would account for a small fraction, 0.004 percent, of the annual diesel fuel use on a national level.

12.2 Air Emissions

Additional air emissions as a result of the final rule can be attributed to added diesel fuel combustion by GCVs collecting ADF-contaminated st ormwater and from anaerobic treatment of ADF. Emissions from these sources are discussed below.

12.2 .1 Emissions from GCV Collection

As discussed in Section 12.1, EPA conservati vely estimated that GCVs collecting ADFcontaminated stormwater at airports will cons ume an additional 354,500 gallons per year of No. 2 diesel fuel. To estimate air emissions related to combustion of No. 2 diesel fuel in GCVs’Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 12 – Non-Water Quality Impacts

167 

### internal combustion engines, EPA used published emission factors for internal combustion engines (U.S. EPA, 1996 AP-42). The Agency sele cted emission factors for gasoline and diesel industrial engines rather than on-road mobile sources because the emission factors for the industrial engines include equipment such as forklifts and industrial sweepers and scrubbers (U.S. EPA, 1006 AP-42). To estimate emissions from the GCVs, EPA first converted the additional 354,500 gallons of diesel fuel to million British Thermal Units (MMBtu) and then applied the appropriate emission factors (U.S. EPA, 1996 AP-42). Table 12-2 shows the estimated increase in criteria pollutant emissions associated with the use of GCVs. Additional details regarding emissions from GCVs are contained in a memorandum titled Air Emissions from Airport Deicing Collection and Treatment Technologies (ERG, 2008b).

Table 12-2. Estimated Incremental Pollutant Emissions from GCVs

Criteria Pollutant Diesel Fuel Consumption in

GCV Internal Combustion Engine (gal/yr) Diesel Fuel Consumption in GCV Internal Combustion Engine (MMBtu/yr) 1 Emission Factor for Diesel Fuel Combustion in Internal Combustion Engine (lbs/MMBtu) 2 Estimated Annual Emissions from GCVs Burnin g Diesel Fuel (tons/yr)
Carbon Monoxide 354,500 49,630 0.95 24
Carbon Dioxide 354,500 49,630 164 4,070 Nitrogen Oxides 354,500 49,630 4.41 109
Sulfur Dioxide 354,500 49,630 0.29 7
PM 10 354,500 49,630 0.31 8

1 Heat content of diesel fuel is approximately 140,000 Btu/gal per Perry’s Chemical Engineers Handbook, 6th Edition, Figure 9-4.
2 Emission factors from EPA Compilation of Emission Factors AP-42. PM 10 – Particulate matter less than 10 um.



### The annual emissions provided in Table 12-2 indicate that an a dditional 4,070 tons per year of carbon dioxide would be emitted from GCVs combusting additional diesel fuel to comply with the regulatory options eval uated in the final rule. Carbon dioxide is the primary greenhouse gas attributed to climate change; although 4,070 additional tons per year appears to be considerable, the amount is very small relative to other sources. For exam ple, in 2006, industrial facilities combusting fossil fuel s emitted 948 million tons of CO 2 

### equivalents. An additional 4,070 tons per year from GCVs is an increase of 0.0004 percent in the overall CO 2 

### emissions from all industrial sources (U.S. EPA, 2008).

Comments provided by industry on the proposed rule correctly indicated that additional nitrogen oxides would be emitted by equipment constructing the ADF-contaminated stormwater collection systems, the AFB treatment system, a nd any ancillary systems such as roadways and storage tanks. According to comments, the Environmental Assessment for the Portland ADF collection and treatment system estimated annual nitrogen oxide emissions at 4.48 tons/yr during construction. Construction of th e ADF collection and treatment system in Portland was estimated to occur over approximately 2.5 years, resulting in total nitrogen oxide emissions of 11.2 tons. Based on the number of in-scope airports that would potenti ally require construction under EPA’s Option 1, total construction-related nitrogen oxide emissions will be approximately 168 tons. In comparison, EPA estimated total nitroge n oxide emissions in th e United States at 18.3 million tons (U.S. EPA, 2005).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 12 – Non-Water Quality Impacts

168 

### 12.2.2 Emissions from AFB Treatment Systems

Anaerobic digestion of glycols found in ADF-c ontaminated stormwater generates biogas containing approximately 60 per cent methane and 40 percent carbon dioxide. Airports installing AFBs to treat ADF-contaminated stormwater are e xpected to burn a portion of the gas in on-site boilers to maintain reactor temperature. The re mainder of gas can be either combusted in a microturbine for electricity generation or flared. Regardless of the combustion technology, nearly all biogas generated by AFBs is conve rted to carbon dioxide, the primary green house
gas. Table 12-3 shows biogas generation and potentia l carbon dioxide emissions from AFB treatment systems for the co sted collection scenario.

Table 12-3. Potential Air Emission s from AFB Treatment Systems

Regulatory Scenario Total COD Removal (pounds/yr) Potential Biogas Generation (million ft 3 /yr) 1 Potential Carbon Dioxide Generation (tons/yr) 2 40% ADF Capture 16,602,900 129 3,730

1 Calculation based on 8 cubic feet of biogas per lb COD removed. Biogas is 60% methane and 40% CO 2 . 2 Assumes 99.9 percent of biogas is converted to CO 2 during combustion.



### Carbon dioxide is the primary greenhouse ga s attributed to climate change; although 3,730 additional tons per year for 40 percent ADF capture appears to be considerable, the amount is very small relative to ot her sources as discussed in 12.2.1.

12.3 So lid Waste Generation

AFB bioreactors will generate sludge that will require disposal, likely in an off-site landfill. To estimate the potential for annual sl udge generation by AFB bioreactors treating ADFcontaminated stormwater under Option 1, EPA firs t estimated the potential COD removal for the collection and treatment scen ario and then applied published anaerobic biomass yield information (Metcalf & Eddy, 1979) to estimate potential total sludge generation on a national basis. The biomass yield calculation, which simply multiplies the COD removal by the yield, is a rough method of estimating sludge generation and does not account for other factors such as degradation or inorganic materi al (e.g., AFB media) that may be entrained into the sludge. However, this method does provide an order of magnitude estimate of sludge generation that can be compared to other types of common biological treatment systems to determine if AFB sludge generation would be unusually high at air ports treating ADF-contaminated stormwater.

Table 12-4 shows the total COD removal for the collection and treatment scenario and the estimated sludge that would likely require disposal. This sludge is expected to be nonhazardous and can be disposed of in a munici pal landfill. Detailed calculations showing how EPA estimated biomass amounts are provided in a memorandum entitled Estimated Sludge Generation from AFBs Treating ADF-Contaminated Stormwater (ERG, 2008c).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 12 – Non-Water Quality Impacts

169 

### Table 12-4. Estimated Sludge Generation from AFB Bioreactors Treating ADFContaminated Stormwater

Regulatory Scenario Total COD Removal (pounds/yr) 1 Anaerobic Biomass Yield (lbs biomass/lb COD removed) 2 Total Sludge Generation (dry tons/yr) 40% ADF Capture 16,602,900 0.03 271

1 Total COD removal from all AFB bioreactors that may be installed at airports.
2 Biomass yield from Metcalf and Eddy.


### To provide some perspective on the potentia l total amount of biomass produced annually by the AFB biological reactors tr eating ADF-contaminated stormwater, EPA compared the total biomass generation data in Table 12-4 to the national biosolids estimates for all domestic wastewater treatment plants throughout the Unit ed States. According to EPA’s Municipal and Solid Waste Division, approximately 8.2 million dr y tons of biosolids will be produced in 2010 (U.S. EPA, 1999). Using the biosol ids generation amount shown in Table 12-4 (271 tons/yr), EPA estimates that AFB bioreactors treating ADF-contaminated stormwater would increase biosolids generation in the United St ates by approximately 0.003 percent.

12.4 Su mmary
EPA reviewed the potential non-water quality impacts of collecti on and treatment of spent ADF using plug and pump with GCVs co mbined with an AFB treatment system and determined that there was an insignificant increase in energy usage and generation of air emissions and solid waste.

EPA then determined that the other regulat ory options under consideration would have similarly insignificant impacts because the other regulatory options involve fewer or no GCVs and smaller or no treatment system. Based on this evaluation of non-water quality impacts, EPA concludes there are no non-wate r quality impacts associated with today’s final rule.

12.5 Refe rences

Bouwer, H. 1978. Groundwater Hydrology. McGraw Hill Press.

ERG. 2008a. Memorandum from Mark Briggs (ERG ) to Airport Deicing Ad ministrative Record. Energy Requirements for ADF-Contaminat ed Stormwater Collection and Treatment Alternatives . (December) DCN AD01166

ERG. 2008b. Memorandum from Mark Briggs (ERG ) to Airport Deicing Ad ministrative Record. Air Emissions from Airport Deicing Collectoin and Treatment Technologies . (December) DCN AD01165

ERG. 2008c. Memorandum from Mark Briggs (ERG ) to Airport Deicing Ad ministrative Record. Estimated Sludge Generation from AFBs Treating ADF-Contaminated Stormwater . (December) DCN AD01164

Metcalf and Eddy. 1979. Wastewater Engineering, Treatment/Disposal/Reuse, Second Edition. McGraw Hill Press.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 12 – Non-Water Quality Impacts

170 

### U.S. Code Title 15, Commerce and Trade, Chap ter 6. 2007. Weights and Measures and Standard Time. (January).

U.S. DOE. 2006. Department of Energy, Energy Information Administration (EIA), No. 2 Fuel Oil All Sales/Deliveries by Prime Supplier. DCN AD00919.

USEPA. 1996. Compilation of Air Pollutant Emission Factors (AP-42), Fifth Edition, Section 3.3. U.S. Environmental Protecti on Agency. Washington, D. C.

USEPA. 1999. Biosolids Generation, Use and Disposal in the United States. U.S. Environmental Protection Agency. Washingt on, D. C. EPA 530D-R-99-009.

USEPA. 2005. Summary of Nitrogen Oxides Emissions

. U.S. Environmental Protection Agency. Available online at http://www. epa.gov/air/emissions/nox.htm#noxnat.

USEPA. 2006. Airport Deicing Questionnaire . U.S. Environmental Protection Agency. Washington, D.C. DCN AD00354.

USEPA. 2008. Inventory of U.S. Greenhouse gas Emissions and Sinks: 1990 – 2006. U.S. Environmental Protection Agency. Washi ngton, D. C. (April). EPA 430-R-08-05.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

171 

### 13. L IMIT ATIONS AND 

### S TANDARDS 

### : D ATA 

### S ELECTION AND 

### C ALCULATION



### This section describes the data selection and statistical methodology that EPA used to calculate the final rule limitations for the Airpor t Deicing Category. As desc ribed in this section, the effluent limitations and standards account for variation in treatment performance of the model technology. For simplicity, the following di scussion refers only to effluent limitation guidelines; however, the di scussion also applies to new source standards.

EPA is finalizing limitations for COD and ammonia as nitrogen (the latter as a compliance alternative), and Section 13.1 briefly describes the pollutant parameters. Section 13.2 provides an overview of EPA’s data review and selection process. Section 13.3 describes EPA’s data conventions. Sections 13.4 and 13.5 descri be the COD and ammonia as nitrogen data selected as the basis of the final limitations . Section 13.6 describes the percentile basis and calculations used for the limitati ons. Section 13.7 describes achiev ability and compliance related to the limitations.

13.1 Sele cted Pollutant Parameters

As described in Section 6, th ere are a number of pollutants associated with discharges from airport deicing operations. EPA is setting effluent limitations for two pollutant parameters, COD and ammonia. This section briefly describes the pollutant parameters and the chemical analytical methods used to measure their concentrations.

13.1 .1 COD

COD is a measure of the total organic matte r content of both wastewaters and natural waters. Measurement of COD can be used to ra pidly recognize deterior ation in wastewater treatment plant performance and the need for co rrective action. EPA evaluated data collected by the Albany International Airport in New York a nd by EPA. The Agency evaluated data for COD that was measured using EPA Method 410.4 and Hach 8000, both of which are approved for compliance monitoring in 40 CFR Part 136. EPA measured COD using Method 410.4, and Albany Airport used Hach 8000. Data from the two methods are directly comparable.

Method 410.4 is a colorimetric procedure with a measurement range of 3 to 900 mg/L for automated procedures and a measurement range of 20 to 900 mg/L for manual procedures. The Hach 8000 method is a colorimetric procedure that utilizes a preliminary digestion procedure and can be used for various concentration ranges. A user has the option of pur chasing three different sets of reagents and standards. The first has a measurement range of 0 to 40 mg/L; the second, 0 to 150 mg/L; and the third, 0 to 1500 mg/L. The i ndustry data had a lower measurement limit of 2.0 mg/L.

13.1.2 Ammonia as Nitrogen (Ammonia)

Ammonia as nitrogen (ammonia) is generated as a by-produc t of using urea-containing products for deicing operations. Ammonia can be directly toxic to fish and other aquatic organisms and can reduce ambient dissolved oxyge n concentrations in re ceiving surface waters. In the data EPA evaluated, ammonia was measured using Methods 350.1 and 350.2, both of which are approved for compliance monitoring in 40 CFR Part 136. Albany Airport suppliedTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

172 

### data that was generated using Method 350.1 (ERG, 2008), and EPA used Method 350.2. Both methods produce comparable results.

Method 350.1 is an automated co lorimetric method that uses a continuous flow analytical system and has a detection range of 0.01 to 2.0 mg/L. Method 350.2 utilizes either colorimetric, titrimetric, or electrode proce dures to measure ammonia. Me thod 350.2 has a lower measurement range limit of 0.20 milligrams per liter (mg/L) for the colorimetric and electrode procedures and a lower measurement range limit of 1.0 mg /L for the titrimetric procedure.

13.2 Over view of Data Review and Selection

As described in Sections 13.4 and 13.5, EPA qu alitatively reviewed all the available influent and effluent data fo r COD and ammonia. For purposes of limitation development, data are defined to be numerical values resulting fr om laboratory determination of pollutants in physical samples collected from influent and e ffluent wastestreams. A laboratory expresses the results of its analysis either numerically or as “not quantitated” for a pollu tant in a sample. When the result is expressed numerically, the pollutant was quantitated, or mo re commonly referred to as “detected,” in the sample. The definition incl udes measured values (e.g., 10 mg/L) and values reported as being below some level of quantif ication (e.g., <10mg/L). The latter are often referred to as “nondetected” and are usually reported with a “d etection limit.” (EPA also uses terms such as “quantitation limit” in other doc umentation.) The definition of “data” excludes estimated values and statistical summ aries, such as averaged values.

This section describes EPA’s review of th e available data. Section 13.2.1 describes the criteria that EPA applied in selecting data fo r the development of the final limitations. Section 13.2.2 describes other consideratio ns that were evaluated as part of the data review.

13.2.1 Da ta Selection Criteria

This section describes the criteria that EPA applied in selecting data to use as the basis for the final effluent limitations. EPA has used thes e or similar criteria in developing limitations and standards for other industries. EPA uses these cr iteria to select data th at reflect consistently good performance of the model technology in tr eating the industrial wastes under normal operating conditions. Model technol ogy is technology that is care fully designed and diligently operated. The following paragraphs de scribe the criteria and modifi cations specific to the Airport Deicing Category.

One criterion generally requires that the in fluent and effluent from the treatment components represent typical wast ewater from the industry, with no incompatible wastewater from other sources (e.g., sanitary wastes). By applying this criterion, EPA selects only those facilities where the commingled wastewaters did not result in s ubstantial dilution, unequalized slug loads that result in frequent upsets and/or overloads, more concentrated wastewaters, or wastewaters with different types of pollutants than those generated by the categorical (i.e., airport deicing) wastewater.

A second criterion typically ensu res that the pollutants were present in the influent at sufficient concentrations to evaluate treatment ef fectiveness. To evaluate whether the data meet this criterion for the final rule, EPA often uses a “long-term average test” for sites where it has paired influent and effluent da ta. EPA has used such comparisons in developing regulations forTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

173 

### other industries (e.g., the Iron and St eel Category (USEPA, 2002)). Th e test looks at the influent concentrations to ensure a pollutant is present at sufficient concentration to evaluate treatment effectiveness. If a pollutant fails the test (i.e., is not present at a treatable concentration), EPA excludes the data for that pollutant at that faci lity from its long-term average and variability calculations. In this manner, EPA would ensure th at the limitations resulted from treatment and not simply the absence or substantial dilution of that pollutant in the wastestream. If industry supplies EPA with effluent data, but not the co rresponding influent data, EPA may choose to use the effluent data without perf orming a long-term average test provided it determines that the pollutant would have been present at consistently treatable concen trations at the facility. This approach would satisfy EPA’s objective to include as much data from as many facilities as possible in the calculation of limits.

A third criterion requires th at the facility must have th e model treatment technology and demonstrate consistently diligent operation. The Ag ency may include facilities with treatment or performance that is equivalent to the mode l technology, but this is rare. EPA generally determines whether a facility meets this criterion based upon site visits, ability to comply with its existing discharge requirements, discussions with facility management, and/or comparison to treatment system performance at other faciliti es. EPA often contacts f acilities to determine whether data submitted were representative of normal operating conditions for the facility and equipment. Based on this review, EPA typically e liminates facilities that experience repeated operating problems with their treatment systems. In addition, EPA typically excludes data when the facility has not optimized its treatment. Fo r example, facilities may use the model technology as a pretreatment step before sending the wast ewater to a POTW and consequently might not fully optimize its system.

A fourth criterion typically re quires that the data cannot re present periods of frequent unequalized slug loading treatmen t upsets or shut-down periods 7 

### because these excursion data do not reflect performance that would be expect ed from well-designed and operated treatment systems. Furthermore, it would not be appropriate for the limitations to be based, in part, upon data reflecting extreme events that are beyond th e control of the facil ity, because regulatory provisions at 40 CFR 122.41(n) woul d apply to such circumstances. More specifically, after the final limitations are incorporated into permits, EPA expects that, when such events occur, the facility would abide by the pro cedural requirements in §122.41(n) to obtain an affirmative defense to any potential enforcement action.

In applying the fourth criterion, EPA evaluate s the pollutant concentr ations, flow values, mass loadings, plant logs, and other available information. As part of this evaluation, EPA typically asks the facility about process or treat ment conditions that may have caused extreme values (high and low). EPA may consequently id entify certain time periods and other outliers in the data that reflect poor performance by an otherwise well -operated site.

7 EPA applies this criterion to data from two types of sh ut-downs. First, treatment systems are sometimes halted to control upset conditions. As part of the recovery activ ities, the facility may pump out wastewater from the equipment (e.g., tanks) which contains highly concentrated wastes associated with the upset. Second, the facility may shut down its operations for maintenance and other at ypical operations. During these periods, the facility may still operate its treatment system, but typically discharges effl uent associated with atypical influent. For example, the influent might include cleaning solvents instead of process wastewater.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

174 

### EPA also applies the fourth cr iterion in its review of da ta corresponding to “start-up” periods, an adjustment period that most industr ies incur only when installing, acclimating, and optimizing new treatment systems. During this ad justment period, the concentration values tend to be highly variable with occasional extreme values (high and low). After this period, the systems should operate at steady state for years with relatively lo w variability around a long-term average. Because start-up conditions typica lly reflect one-time operating conditions, EPA generally excludes such data in developing the limitations. In cont rast, EPA expects airports to encounter start-up operations at the start of every deicing season because they probably will cease treatment operations during warmer months . Because this adjustment period will occur every year for the Airport Deicing Category, EPA is including start-up data in the data set used as the basis of the limitations. However, through its application of the ot her three criteria, EPA would exclude extreme conditions that do not de monstrate the level of control possible with proper operation and control ev en during start-up periods.

In part, by retaining start-up data for limita tions development, the limitations will be achievable because EPA based these limits on t ypical treatment during the entire season. Once the treatment system reaches steady state, EP A expects a typically we ll-designed and operated system to run continuously until the end of the deicing season.

13.2.2 Other Considerations in Data Selection

In comments on proposed regulations acr oss a range of indus try categories and subcategories, industries often s uggest that EPA consider additiona l criteria in sel ecting data as the basis of the limitations. EPA routinely evalua tes whether the suggested criteria are relevant and should be considered as it develops new regulations. As explained below, EPA also considered additionalcriteria for the airport deicing rulemaking, but determined that they were not relevant in selecting data as the basis of the final limitations. EPA’s rationale is consistent with its findings for other industries.

Commenters often suggest a criterion related to the size of facilities because of concerns about a perceived impact of volume, or flow, of wastewater on treatment performance. In considering this issue for the air port deicing industry, EPA concluded that the size of the airport, collection technology, and ot her features by themselves would not affect the performance of the treatment system. Instead, the airport size a nd water flow would determine the size of the treatment system, rather than its performance. EPA expects that each airport would build and operate a system that is sized appropriately fo r its volume of wastewater . Because the method of treatment is the same regardless of the flow, properly sized systems should all perform in the same manner, and achieve the same effluent con centrations. Before reaching this conclusion for airport deicing and other industr ies, EPA reviewed treatment t echnologies such as biological treatment, oil-water separators, dissolved air floatation, and settli ng tanks. EPA's record supports the finding that, for a variety of industrial sectors, well-operated and designed treatment systems treat different wastewaters with varying flows to a narrow range of effluent concentrations (USEPA, 2010).

In addition, commenters typically suggest a criterion that woul d require a minimum number of facilities be used as the basis of the limitations. Such suggestions are based upon two main concerns. First, commenters are concerned th at the limitations do not reflect treatment from a range of typical influents, because the concentr ation levels vary from facility to facility.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

175 

### Second, commenters are concerned th at not all facilities could ach ieve the same high level of performance using the model technology. For the firs t concern, as part of its evaluation of the effect of flow described above, EPA also c onsidered the impact of influent pollutant concentrations. EPA found that well-operated and designed treatment systems are capable of treating the wastewaters to a narr ow range of effluent pollutant concentrations. For the second concern, EPA only needs to demonstrate that the model technology can be operated at the level of performance on which the limitations are based. EPA’s selection of the model technology used at the Albany International ai rport as the basis of the limitati ons is appropriate because that facility demonstrates that the technology can achieve the levels reflected in the final limitations.

The CWA authorizes EPA to ba se BAT/NSPS limitati ons and standards on the performance of a single facility and it is not unusual for EPA to base effluent limitations on data from a single facility. For ex ample, in the Organic Chemicals, Plastics and Synthetic Fibers (OCPSF) effluent guideline promulgated in 1987, EPA based 38 percent of the limitations on the performance of a single facility (USEPA, 1987). Courts have recognized that EPA must act on the information it has and ne ed not wait for perfect information(e.g., see BASF Wyandotte Corp. v. Costle, 598 F.2d 637, 652-653 (1st Circuit, 1979)).

13.3 Conventions for Modeling Multiple Data Sets from the Same Facility

This section describes EPA’s conventions for modeling multiple data sets from the same facility. Data from a particular facility are some times collected at different times, from different treatment units, or by different organizations. In such cases where multiple data sets exist for the same facility, EPA often statistica lly models the data as if each data set represents a different facility. This section describes c onventions applied to th e data from the air port deicing industry.

EPA generally considers data from different time periods to characterize different operating conditions due to changes such as management, personnel, and procedures. Because EPA expects airports to operate treatment systems only for a limited time each year, it considered whether the conditions and performa nce for each deicing season tend to vary in a manner that more appropriately reflects differe nt treatment systems. Because it may better capture the variability of airport deicing operations under a range of conditions, EPA has calculated the final limitations us ing all of the data, without rega rd to season. For informational purposes, the data and summar ies are presented by season.

EPA generally uses data from separate treatment units (depending on the rulemaking, also called “trains” or “systems”) as if they characterized separate facilities. EPA has determined this is appropriate because the units were operate d separately. Even if the wastes were generated by the same processes or drawn from the same storage pond, EPA considers that the performance of each system can vary due to slightly differe nt influents, equipment, and other factors.

EPA generally considers data from different organizations to characterize different collection methods and analytical methods. Th e different organizations typically are EPA sampling teams and the facility’s monitoring crew at the treatment system. EPA often separates such data into multiple data sets, to better model the variability consistent with the use of a single analytical method and the same collection procedures. Consistent use of a single method and procedure is often required by permits and is ty pical of compliance monitoring. Therefore, theTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

176 

### Agency generally uses this convention to model typical variability that each facility would experience in compliance monitoring activities. EPA then determines which, or all, multiple data sources are appropriate choices as the basis of the limitations.

1 3.4 COD: Data Selected as Basis of Final Limitations

In establishing the final limitations, EPA revi ewed COD data from a treatment plant at the Albany International airport, which used the model BAT. (Selection of the model technology is described in Section 8 and in the preamble to today’s rule.) EPA collected COD data during a sampling episode at Albany International airport and obtained several years of monitoring data and other information from the airport. After evaluating these data, EPA determined that the Albany data were the only available pe rformance data from the model technology. 8 

### Thus, all other data sets were excluded by applying the th ird criterion in Section 13.2.1, because they did not demonstrate the performance of the model technology. The following se ctions describe the Albany airport and apply the criteri a in identifying the specific data points used as the basis of the final limitations.

1 3.4.1 Albany Treatment System

EPA based the final limitations for COD upon data from Albany Airport’s treatment system. This system consists of two identical units that are consistent with EPA’s model technology described in Section 8. Th e airport diverts stormwater fr om deicing operations into a lagoon. Facility personnel then pump water from the lagoon to one anaerobic unit or the other for treatment. The airport generally operates the tw o treatment systems in parallel, but sometimes runs them in series. At the end of each unit, re gardless of whether the system is in parallel or series, the airport monitors COD concentrations each morning by collecting grab samples to evaluate the treatment performa nce. These locations are labeled as ArprtR-101 and ArprtR-102 in Figure 13-1 . During its five-day sampling episode conducted from February 5-9, 2006, EPA measured COD and ammonia concen trations in composite samples collected at a point (labeled EPA_SP-2) where the two units combine into a si ngle flow before entering an aerobic polishing pond for more treatment. After this step, the airp ort typically directly discharges waste into Shaker Creek, a tributary of the Mohawk River, which has been classified as a New York State Class A drinking water stream. As a consequence, the airport is required to meet stringent limitations when it discharges directly to the cr eek. In warmer weather (i.e., when the soil is 50 degrees or warmer), the airport sometimes uses the treated wastewater fo r irrigation. In addition, the airport is able to discharge to a POTW, although it seldom does.

8 Akron Canton Airport in Ohio started operating the model technology in mid-November in 2007. When EPA was completing its technical analysis of the industry in late sp ring 2008, the airport’s treatment unit was not operating at full capacity.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation



### Lagoon Anaerobic unit #1

Anaerobic unit #2 Aerobic polish

ArprtR-102

(COD)

AprtR-101

(COD)

EPA_SP-2 (COD, Ammonia)



### Figure 13-1. Simplified Drawing of Albany Airport Treatment System and Sample Points

As the basis for the final limitations for COD, EPA selected the data at sample points ArprtR-101 and ArprtR-102 because each unit is the same as the model treatment system that EPA identified in Section 11. The airport has m onitored its performance for a relatively long time and provided EPA with data from De cember 1, 1999, through April 10, 2009 (10 deicing seasons). Because the influent was highly concentr ated, it was not necessary to perform the longterm average test described in Section 13.2. 9



### DCN AD01181 provides the influe nt and effluent COD data as originally submitted by the airport and the data are graphically di splayed in the statistical support memorandum (USEPA, 2006). The following sections describe the exclusion of data collected from the EPA sampling episode and the airport’s self-monitoring data.

1 3.4.2 COD Data from EPA Sampling Episode at Albany

During EPA’s sampling episode, EPA and the airport collected separate sets of samples (see Table 13-1 analytical results). At sample point EPA_SP-2, EPA collected samples of the combined flow from the two units. In contrast, th e airport monitored the effluent directly from each unit at sample points ArptR- 101 and ArptR-102 and filtered th e samples prior to analyzing for COD. Both sets of samples demonstrate the performance of the model technology because no additional treatment steps exist between the ai rport sample points and EPA’s sample point. Rather than include data from tw o different sources (i.e., EPA and the airport) for the same dates, EPA preferentially selected the ai rport data because they were part of longer-term monitoring. Although the EPA data were therefore excluded as the basis of the limitati ons, EPA notes that all of the values are less than the value of 271 mg/L for the final daily maximum limitation.

9 EPA typically compares average influent levels to a multi plier of 5 to 10 times the quantitation limit (or reporting limit). As explained in Section 13.1.1, the airport data ha d a lower measurement limit of 2.0 mg/L. Thus, in the longterm average test, EPA would probably have compared the influent data to a reference level of 10 to 20 mg/L. However, because the minimum influent value of 100 mg/L exceeded this range of potential reference values, the average values also will meet the requirements of the long term average test.

177Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

178 

### Table 13-1. COD: EPA and Alba ny Airport Self-Monitoring Effluent Data Collected During EPA’s Sampling Episode

Sample Date COD Concentrations (mg/L) EPA Sampling Episode Data Airport Self-Monitoring Data

Original Sample Field Duplicate (where collected) AprtR-101 AprtR-102
2/5/06 72 29 74
2/6/06 228 208 53 108
2/7/06 92 177 56 94
2/8/06 81 31 90
2/9/06 193 48 96



### 1 3.4.3 COD Self-Monitoring Data from Albany Airport

The airport typically runs the two units in parallel. EPA considers each unit’s performance, when operated in this manner, to be consistent with the model technology. In its evaluation of the data from each unit, EPA applied the criteria and other considerations described in Section 13.2. As a result of this evaluation, EPA excluded data associated with atypical operations, influent concentrati ons reported as zero, estimated values, and poor performance. The exclusions are described below.

By applying the third criterion in Secti on 13.2.1, EPA excluded all periods when the units were operated in series because the data di d not reflect treatment by the model technology. Table 13-2 identifies these time peri ods by deicing season (e.g., Season99 started in 1999 and continued into 2000). During these periods, one un it provided initial treatment and the second provided additional treatment. Although the facil ity reported effluent values from each unit during this period of operating in series, it only discharged the e ffluent from the second unit in the series. EPA considers the effluent data from the first unit to reflect less than optimal performance, because the operators presumably would have not optimized treatment as they intended to treat the wastes a second time (criteri on 3). EPA considers the effluent data from the second unit to characterize treatment of atypical influent (i.e., e ffluent that had been treated by the first unit).Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

179 

### Table 13-2. COD: Dates Excluded Because Units Operated in Series

Season Number Days Excluded Beginning Date End Date
Season99 32 2/9/2000 3/11/2000
Season00 31 12/12/2000 1/11/2001
Season01 3 2/7/2002 2/9/2002
Season02 8 11/17/2002 11/24/2002
3 4/5/2003 4/7/2003
Season05 25 1/10/2006 2/3/2006
Season06 79 1/15/2007 4/3/2007
Season07 31 2/2/2008 3/3/2008
Season08 25 11/17/2008 12/11/2008



### EPA excluded effluent values for both units wh en the influent concentration was reported as “zero” for two reasons. First, if COD could not be detected in the influent (criterion 2), then the effluent concentrations woul d not reflect any additional treat ment. Second, it appears that the plant used this convention to indicate shut-downs of the system (criterion 4). Table 13-3 identifies the dates when the influent c oncentration was report ed to be zero.

Table 13-3. COD: Dates Excluded Because Infl uent Concentration Reported as Zero

Season Date
Season01 6/14/2002
Season02 11/16/2002
Season06 4/10/2007



### EPA also excluded any values that were es timates because they did not meet EPA’s definition for “data” described in Section 13.2. There were two types of estimated values. One type was in italics in the facility’s spreadshee ts, indicating that the operator’s log noted issues with the sample or its analysis, and thus, the reported value was an estimate. The second type was a series of identical values reported over consecutive monitoring days. Although it is possible to find exactly the same pollutant concen trations on consecutive days, variations from day to day are more typical. In response to EPA’ s questions about the strings of identical values, the facility stated that it sometimes repeated the last known number when they did not monitor (ERG. 2008a). To model the variabil ity likely to be present in th e effluent, EPA a ssumed that the first non-zero value was the only day when COD was monitored when three or more days had identical values for the same unit. Therefore, EP A retained the value for the first day and deleted the (identical) values on subsequent days for that unit. If the values were zero, EPA assumed that the unit was not operating and excl uded the entire time period, in cluding the first reported zero value. The statistical support memorandum (U SEPA, 2010) identifies these exclusions.

In addition, by applying the f ourth criterion in Section 13.2, EPA excluded periods that did not reflect the typical performa nce of the technology. As shown in Table 13-4 , these exclusions included treatment system upsets an d method error. For example, EPA excluded the maximum value of 1,283 mg/L recorded at Arpr tR-101 on 3/21/2001 because it was inconsistent with the other data values during that time period. The plant management agrees that the valueTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

180 

### does not reflect normal operations and suspects th at it was likely a sample with high solids content (ERG. 2008b).

Table 13-4. COD: Dates Excluded Beca use of Performance Excursions

Season Number Days Excluded Beginning Date End Date Reason
Season99 11 12/1/2000 12/11/2000 System Upset
Season00 42 1/12/2001 2/22/2001 System Upset
1 3/20/2001 3/20/2001 Method Error
1 3/21/2001 3/21/2001 System Upset



### After the exclusions were incorporated, mo re than 2,500 measurements of COD remained and were used as the basis of the final limitations. Table 13-5 summarizes the data. The statistical support memorandum (USEPA, 2010) pr ovides a list and plots of the data.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

181 

### Table 13-5. COD: Summary of Albany Airpor t Self-Monitoring Effluent Data After Exclusions

Unit Season COD Concentrations (mg/L) 1
# of Days Standard Deviation Minimum Maximum Median Mean 2

ArprtR_101 Season99 147 50.31 1 326 14.0 28.60
Season00 112 71.93 2 575 64.0 75.46
Season01 168 20.97 9 157 37.0 44.02
Season02 180 64.41 20 655 73.0 86.80
Season03 146 103.19 2 699 50.0 76.32
Season04 140 30.76 2 275 25.0 31.51
Season05 90 18.08 8 162 29.5 31.56
Season06 62 24.08 1 136 17.0 23.10
Season07 124 98.07 9 1042 41.5 54.48
Season08 120 59.85 15 674 35.0 42.74

ALL 1289 66.67 1 1042 37.0 52.28

ArprtR_102 Season99 141 17.41 1 93 11.0 16.85
Season00 117 51.50 11 393 55.0 63.09
Season01 165 20.23 10 168 35.0 40.01
Season02 183 51.73 25 685 51.0 57.61
Season03 147 30.03 1 210 60.0 63.12
Season04 145 73.96 2 725 76.0 87.42
Season05 95 33.21 22 275 72.0 77.19
Season06 62 41.68 2 148 46.5 61.34
Season07 98 10.01 12 58 34.0 33.70
Season08 120 24.92 12 282 37.0 39.07

ALL 1273 45.65 1 725 45.0 53.40

1 In this summary, nondetected values are set equal to the detection limit.
2 The mean is calculated as the arithmetic average.



### 1 3.5 Ammonia: Data Selected as Basis of Final Limitation

For ammonia, EPA is promulgating a comp liance alternative with a daily maximum limitation for airports that use de icers containing urea on the runway s. This section describes the data selected as the basis of the final limitation for ammonia.

After evaluating the available data, EPA transf erred the 1-day-lag serial correlation value from the AFB technology, which is the model t echnology for COD. This transfer was necessary because an AFB system by design creates ammoni a as a by-product of wastewater treatment. Consequently, AFB discharges could have highe r ammonia concentrations than typically found in airfield stormwater when airfield deicers c ontaining urea are not used. If the treated aircraft deicing stormwater discharges then were discharged to the same pipe as the runway wastewater, the airport might have difficulties complying w ith the ammonia limitation. EPA also confirmed that ADF treatment provided less concentrated di scharges than observed from the application of urea products (ERG. 2009). For these reasons, EPA de termined that it was appropriate to use theTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

182 

### ADF data as a basis of limitations that would apply to discharges a ssociated with runway deicing.

As it had for COD, EPA initially evaluated the Albany data for se tting final limitations for ammonia, because EPA had data on the performance of its model technology. In contrast to its practice of monitoring COD at the end of each treatment unit, the airport monitored ammonia at its permit compliance point after additional treatment provided by an aerobic polishing step. The anaerobic polishing step would result in decreased ammonia concentrations and would not represent ammonia discharges from using urea on airfields. Thus, to promulgate an effluent limit consistent with the model technology, EPA used the EPA data and excluded the Albany ammonia data (criterion 3).

Instead, because they reflect the capability of the model treatment system, EPA used its sampling data from EPA_SP-2, shown in Table 13-6 , as the basis of the final ammonia limitations. (Section 13.6 describes field duplicates and the importa nce of daily values for the limitation calculations.) In anal yzing samples from this episod e, the laboratory achieved a detection limit of 0.05 mg/L. During the laboratory ’s quality assurance st ep of the chemical analysis, it detected ammonia in the laboratory preparation bl ank at a concentration of 0.069 mg/L. Other quality assurance parameters, ini tial calibration blanks a nd continuing calibration blanks, were between 0.052 mg/L and 0.054 mg/L . The ammonia results for all samples are greater than 10 times the blank re sult, with the excepti on of four influent and one source water samples that were not used as the basis of the final limitation. Consequently, EPA determined that the data were of accepta ble quality to use as the ba sis of the final limitation.

Table 13-6. Ammonia: Data from Albany Airport Used to Develop Limitations

Sample Day Ammonia Concentrations (mg/L)

Influent Effluent

Original Sample Field Duplicate (where collected) Daily Value Used in Limitations Calculations
1 ND (0.1) 2.58 2.58
2 ND (0.1) 4.14 3.95 4.05
3 ND (0.1) 4.45 5.54 5.00
4 ND (0.1) 6.12 6.12
5 0.91 6.65 6.65
ND – Not Detected



### 1 3.6 Limitations: Basis and Calculations

The final limitations, as presented in the fi nal rule, are provided as the daily maximum limitations for COD and ammonia. In addition, the notice includes a weekly average limitation for COD. This section defines the limitations (Section 13.6.1) and describes the statistical percentile basis of the limitati ons (Section 13.6.2) and the estima tion of the percentiles for COD and ammonia (Sections 13.6.3). The statistica l support memorandum (USEPA, 2010) describes the calculations used to model the ammonia data.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

183 

### 1 3.6.1 Definitions

Definitions provided in 40 CF R 122.2 describe the limitations in terms of “daily discharge,” which it defines as “the ‘discharge of a pollutant’ measured during a calendar day or any 24-hour period that reasonabl y represents the calendar da y for purposes of sampling.” Therefore, EPA generally arithmetically averages all measurements recorded for each uniquely reported time period (e.g., 12/21/ 2004) before calculating lim itations. EPA refers to this averaged value as the “daily value.”

First, in calculating the limitations, EPA ensu res that it has only one value for each day. Field duplicates are one example of multiple m easurements, and were included in the ammonia data used to develop the final limitations. Field duplicates are two samples collected at the same sample point at approximately the same time, fla gged as duplicates for a single sample point, and measured separately. Because the analytical data from each duplicate pair characterize the same conditions at that time at a single sample point, EPA typically averages the data to obtain one data value for those conditions on that day. For example, Table 13-6 shows the field duplicates and daily, averaged values for ammonia.

Second, EPA uses the daily values in calculati ng the limitations. Definitions provided in 40 CFR 122.2 further describe the “maximum da ily discharge limitation” as the “highest allowable ‘daily discharge.’” The “average weekly discharge limitation” is the “highest allowable average of ‘daily discharges’ over a cal endar week, calculated as the sum of all ‘daily discharges’ measured during a calendar week divided by the number of ‘daily discharges’ measured during that week.”

1 3.6.2 Percentile Basis of the Limitations

EPA uses a statistical framework to establis h limitations that facilities are capable of complying with at all times. St atistical methods are appropriate for dealing with effluent data because the quality of effluent, ev en in well-operated systems, is subject to a certain amount of fluctuation or uncertainty. Statistics is the scie nce of dealing with uncer tainty in a logical and consistent manner. Statistical methods togeth er with engineering analysis of operating conditions, therefore, provide a logical and consis tent framework for analyz ing a set of effluent data and determining values from the data that form a reasonable basis for effluent limitations. Using statistical methods, EPA has derived num erical values for its final daily maximum limitations and weekly average limitations.

The statistical percentiles upon which the limita tions are based are intended to be high enough to accommodate reasonably anticipated variability within control of the facility. The limitations also reflect a level of performance consistent with the CWA requirement that these limitations be based on the best technologies that are properly operated and maintained.

In establishing daily maximum limitations, EPA’ s objective is to rest rict the discharges on a daily basis at a level that is achievable for an airport that targets its treatment system design and operation at the long-term average while allowing for the variability around the long-term average that results from normal operations. This variability means that at certain times airports may discharge at levels that are greater or cons iderably lower than the long-term average. To allow for possibly higher daily discharges, EPA has established the daily maximum limitation at a relatively high level (i.e., the 99t h percentile). Due to routine vari ability in treated effluent, anTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

184 

### airport that discharges consistently at a level near the da ily maximum limitation, instead of the long-term average, may experience frequent va lues exceeding the limitations. For this reason, EPA recommends that airports ta rget the treatment system at the long-term average that it derived for the model technology.

In its derivation of the weekly average limita tion for COD, EPA used an estimate of the 97th percentile of the weekly averages of the da ily measurements. This percentile basis is the midpoint of the percentiles used for the daily maximum limitation (i.e., 99th percentile of the distribution of daily values) and the monthly average limitation (i.e., 95th per centile of the distribution of monthly average values). Courts have upheld EPA’s use of these percentiles, and the selection of the 97th percentile is a logical extension of this practi ce. Compliance with the daily maximum limitation is determined by a single daily value; therefore, EPA feels the 99th percentile provides a reasonable basis for the daily maximum limitation by allowing for an occasional extreme discharge. Because compliance with the monthly average limitation is based upon more than one daily measurement and averag es are less variable than daily discharges, EPA has determined that facilitie s should be able to control the average of daily discharges to avoid extreme monthly averages above the 95th percentile. Similar to the monthly average limitation, compliance with the weekly average limitation also would be based upon more than one daily measurement. However, the airport would monitor for a shorter time and thus would have fewer opportunities to counterbalance highly concentrated daily discharges with lower ones. For this reason, EPA is utilizing a larger percentile for the weekly average limitation than the one used for the monthly average limitation. C onsequently, EPA is usi ng the 97th percentile as an appropriate basis for limiting average disc harges on a weekly basis. EPA also considers this level of control in avoidi ng extreme weekly average discharges to be possible for airports using the model technology.

1 3.6.3 Estimation Procedures for Percentiles

This section describes the estimation pro cedures that EPA used to calculate the limitations for the final rulemaking. Secti ons 13.6.3.1, and 13.6.3.2 describe the estimation procedures used to model the COD data and the June 8, 2009, memorandum on calculation of percentiles (Westat. 2009) descri bes the calculations used by th e statistical software. Section 13.6.3.3 describes the procedures for ammonia.

Table 13-7 summarizes the limitations that EP A established for COD and ammonia. Because of the importance of targeting treatm ent to the long-term average, EPA recommends that facilities design, maintain, a nd operate the treatment system to achieve a long-term average of 52.8 mg/L, which is the median of the av erages from the two units (52.28 mg/L for ArprtR_101 and 53.40 for ArprtR_102, as shown in Table 13-5 ). The allowance for variability, or the ratio of the limitation to the long-term av erage, is 5.13. (EPA usually refers to this allowance as the “variability f actor.”) In other words, the da ily maximum limitation is 5.13 times greater than the long-term aver age achievable by the model t echnology. By targeting the system to the long-term average and controlling its variabili ty within this range, the facility will be able to comply with the limitation.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

185 

### Table 13-7. COD and Ammonia: Final Limi tations with Long-Term Averages and Variability Factors

Parameter Time Period COD Ammonia Limitations (mg/L) Daily Maximum 271 14.7 Weekly Average 154 NA Long-Term Average (mg/L) All 52.8 5.24 Variability Factors Daily 5.13 2.81 Weekly 2.92 NA NA – Not applicable



### 1 3.6.3.1 COD: Daily Maximum Limitation and the 99 th 

### Percentile

For COD, EPA based the final daily maximum limitation on an estimate of the 99 th 

### percentile of the distribution of the daily values. This section describes the percentile estimates and the long-term average.

First, EPA used nonparametric methods to estimate the 99 th 

### percentile of the daily values from each unit. A simple nonparametric estimate of the 99th percentile of an effluent concentration data set is the observed value that exceeds 99 percent of the observed data points. Because EPA had more than 1,200 data points for each unit, it determined that the empirical approach would provide reasonable estimates of the 99 th 

### percentiles.

Second, EPA set the final limitation e qual to the median of the two 99 th 

### percentile estimates, or 271 mg/L. The median is, by definiti on, the midpoint of all available data values ordered (i.e., ranked) from smallest to largest. As result, half of the unit 99 th 

### percentiles are higher than the median and half are lower. (In th is particular case, beca use there are two units, the median is equal to the ar ithmetic average (or mean).)

Table 13-8 summarizes the percentile estimate s for the two units, the minimum and maximum values observed in the data, the 50 th 

### percentiles, and the 99 th 

### percentiles.

Table 13-8. COD: 99 th 

### Percentile Estimates from Each Treatment Unit

Treatment Unit Number of Daily Values Concentrations (mg/L)
Minimum 50 th Percentile Maximum 99 th Percentile ArprtR-101 1,289 1 37 1042 326 ArprtR-102 1,273 1 45 725 216
Median Values 41 271



### 1 3.6.3.2 COD: Weekly Average Limitation and the 97 th 

### Percentile

For the weekly average limitation of COD, EPA first calculated, for each unit, the arithmetic average of the measurements observe d during each week, excluding weekends (to be consistent with the assumed monitoring costs, although permit authorities may specify different monitoring requirements). EPA then used the nonparametric method to derive a 97 th 

### percentile of the more than 200 weekly averages for each unit, and set the final limitation equal to the medianTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

186 

### of the two 97 th 

### percentile estimates, or 154 mg/L. The statistical support memorandum (USEPA, 2010) lists the weekly averages.

Because data were not always available for every weekday during a week, EPA examined whether the weekly averages were affected by th e number of weekdays in cluded in the average. As shown in Table 13-9 , the value of the limitation varied only slightly if the weeks were required to have data for all five days. The June 23, 2009, memorandum on percentiles for weekly averages (Westat, 2009a) provi des a more detailed evaluation.

Table 13-9. COD: Effect of Number of Daily Values in Weekly Averages

Number of Daily Values in Average Unit ArprtR-101 Unit AirprtR-102
Median of 97th Percentiles Number of Weekly Averages 97th Percentile Number of Weekly Averages 97th Percentile
5 155 176.8 157 133.6 155.2
4 or 5 181 176.8 181 133.6 155.2
1 to 5 1 209 162.4 203 145.5 153.95

1 Averages in this row were used as the ba sis of the final weekly average limitation.



### 1 3.6.3.3 Ammonia: Percentile Estimates Based Upon the Lognormal Distribution

Because the ammonia data set had fewer than 100 observations, EPA used a parametric approach to model the data. If a data set comprisese fewer than 100 observations, the best that can be done, using nonparametric methods, is to use the maximum value as an approximate nonparametric estimate of the 99th percentile, bu t this can underestimate the true value. Parametric methods require that a probability distribution be sp ecified, which allows estimation of unknown parameters from the available data. Th e estimated parameters are a function of the defined distribution and the data , and thus the parametric meth od enables the percentiles of effluent concentrations to be computed analytic ally. EPA’s selection of parametric methods in developing limitations for other industries is well documented (e.g., Iron and Steel, Pulp, Paper, and Paperboard, and Metal Products and Machin ery categories). EPA considers the lognormal distribution to be approp riate for the ammonia data, and this section describes its application in estimating the final daily maximum limitation. Th e daily maximum limitation of 14.7 mg/L is based upon an estimate of the 99 th 

### percentile of the lognormal dist ribution of the daily values.

The calculations include an adjustment for possi ble bias due to statistical autocorrelation. The adjusted variance then better reflects the unde rlying variability that would be present if the data were collected over a longer period. When data are said to be positively autocorrelated, it means that measurements taken at specific time intervals (such as 1 day or 2 days apart) are similar. For example, positive autocorrelation would be present in the data if the final effluent concentration was relatively high one day and was likely to remain at similar high values the next and possibly succeeding days. EPA sampling da ta, used as the basis of the limitations, were collected on five consecutive days , and thus, the data may be au tocorrelated, but the length of time was not sufficient for autocorrelation evalua tions. Albany Airport’s self-monitoring data also were not suitable for the evaluation because they were collected at three-week intervals rather than consecutive days. In contrast, the Iron and Steel rule had 244 data points for ammonia that generally were collected on consecutive days , so it was possible to evaluate autocorrelation in the data. Because the model technologies fo r both industries are biological systems, EPATechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

187 

### concludes that the Iron and Steel autocorrelation adjustment is a reasonable transfer that can be used to calculate the airport deicing limitations. 10 

### Table 13-10 summarizes the final long-term average and daily maximum limita tion, with and without the adjustment fo r autocorrelation. The final daily maximum limitation of 14.7 mg/L is 2.8 times greater than the long-term average, of 5.24 mg/L, achievable by the model technology. By targeting the system to the long-term average and controlling its variabilit y within this range, the facility will be able to comply with the limitation. However, ammonia is generated as a by-product of the model technology, and EPA expects the concentrations of ammonia to have similar variab ility to what is being treated (i.e., COD). In contrast to the COD limitations , which are based on a mixture of start-up and steady-state periods, the ammonia limitation is based upon data collected only during steadystate operations.

Table 13-10. Ammonia: Consideration of Auto correlation for Final Limitations, LongTerm Averages, and Variability Factors

Statistical Parameter Adjusted for Autocorrelation? Percent Difference No Yes (Final) Long-Term Average (mg/L) 4.97 5.24 5% Variability Factor 2.25 2.81 25% Daily Maximum Limitation (mg/L) 11.2 14.7 31%



### Unlike COD, EPA is not setting a weekly ammonia effluent limitation. The technology basis for the COD effluent limitations would operate throughout the deicing season with continuous discharges allowing fo r weekly monitoring. In contrast , urea is applied to airfield pavement as needed, and discharg es would occur for a short time after the initial application, as the urea works its way through the stormwater co llection and any associated treatment system that may be present. Most airports would ha ve noncontinuous and somewhat infrequent urea discharges. Consequently, it would be difficult to assume a single value for the monitoring frequency that could reasonably be applied to all airports, rega rdless of climatic conditions.

1 3.6.3.4 Significant Digits for Final Limitations

In presenting the values of the final limitations, EPA rounded the values to three significant digits. EPA used a rounding procedure where values of five and above are rounded up and values of four and below are rounded down. For example, a value of 5.235 would be rounded to 5.24, while a value of 5.234 would be rounded to 5.23.

1 3.7 Achievability of Limitations

EPA promulgates limitations that sites are ca pable of complying with at all times by properly operating and maintaini ng their processes and treatment technologies. As a consequence of using the percentile basis fo r each final limitation, treatment systems that are designed and operated to achieve long-term average levels sh ould be able to comply with the limitations, which incorporate variability, at all times. As verification that the limitations are achievable,

10 EPA has not incorporated a similar adjustment for auto correlation into the data for the COD limitations because the limitation is based upon more than 2500 measurements collected over 10 years, which presumably would show a full range of variability expected by the model technology. (DCNs AD01210 and AD01214)Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

188 

### EPA performs additional statisti cal and engineering reviews, as described in Section 13.7.1. As a result of these reviews, EPA has concluded that these limitations are achievable, and thus EPA expects facilities to comply with the limitations as explained in Section 13.7.2.

1 3.7.1 Statistical and Engineering Review of Limitations

In conjunction with the statis tical methods, EPA performs an engineering review to verify that the limitations are reasonable base d upon the design and expected operation of the control technologies and the air port conditions. The following sect ions describe two types of comparisons. First, EPA compares the final li mitations to the data used to develop the limitations. Second, EPA compares the li mitations to the influent data.

1 3.7.1.1 Comparison to Data Used As Basis for the Limitations

As part of its data evaluations, EPA compared the value of the final limitations to the values used to calculate the limita tions. None of the data selected for ammonia were greater than its final daily maximum limitation that supports the engineering and statistical conclusions that the limitation values are appropriate. Because of the statistical methodology used for the COD limitations, some values were greater than the final limitations.

For COD, appropriately one pe rcent of the values were greater than the final daily maximum limitation, which is consistent with the statistical basis (i.e., use of the 99 th 

### percentile) of the limitation. Table 13-11 lists the data from both units a nd the influent, when one or both effluent values were greater than the limitation. Of the 27 values greater than the final limitation, 20 were from the ArprtR-101 unit, and 7 from Ar prtR-102 unit. Both units had values greater than the final limitation on three date s: 3/31/2001, 1/4/2005, and 12/25/2008.

Of the 412 weekly averages of the COD concentr ations, 12 averages had values that were greater than the final weekly average limitati on of 154 mg/L. Of those 12 averages, 10 were during weeks when the unit also had one or more daily values that were greater than the daily maximum limitation. The statistical support me morandum (USEPA, 2010) identifies the weeks and the corresponding daily values.

1 3.7.1.1 Comparison to Influent

In addition to evaluating the data used as the basis of the limitations, EPA often compares the value of the final limitations to influent concentration levels. In these comparisons, EPA determines if the limitations perform as expected.

As part of its evaluation to determine if the COD limitation was sufficiently stringent to require that the influent be treated, EPA eval uated the COD influent discharges from Albany Airport. As shown in the summary statistics in Table 13-12 , all influent values were greater than the final limitation during nine deicing seasons. For the seas on 06, only two values (1/1/2007 and 1/2/2007) were less than the final limitation. 11 

### This finding confirmed that the final limitation can only be met through treatment.

11 For both dates, the facility reported the same values for influent (100 mg/L), the same values for ArprtR-101 (30 mg/L), and the same estimated values for ArprtR-102.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

189 

### Table 13-11. COD: Dates and Values Great er than Final Limitation of 271 mg/L

Season Date COD Concentrations (mg/L) 1 ArprtR_101 ArprtR_102

Season99 16MAR2000 326 33
23MAR2000 315 93

Season00 01MAR2001 276 232
11MAR2001 288 64
12MAR2001 575 92
22MAR2001 129 393
31MAR2001 357 288

Season02 18MAY2003 (Estimated to be 800) 2 685
19MAY2003 460 95
20MAY2003 655 86
22MAY2003 290 101

Season03 20DEC2003 278 2
03JAN2004 690 36
08JAN2004 387 37
08FEB2004 435 74
09FEB2004 453 49
16MAR2004 316 124
17MAR2004 699 118

Season04 04JAN2005 275 725
04FEB2005 38 360
Season05 09DEC2005 162 275

Season07 09JAN2008 1,042 Out of service
10JAN2008 433 Out of service
Season08 25DEC2008 674 282

1 Bold text indicates effluent values greater than the limitations.
2 This value was not used in calculating the limits because it was an estimated value (see DCN AD01246)Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

190 

### Table 13-12. COD: Summary Statistics of Influent Concentrations

Season #of Days COD: Influent Concentration (mg/L)
Standard Deviation Minimum Maximum Median Arithmetic Average

Season99 141 1,536 1,000 6,560 2,784 3,242

Season00 115 1,257 1,797 7,950 5,505 5,208

Season01 167 1,505 342 7,105 3,975 3,949

Season02 187 1,825 2,915 10,470 7,270 7,144

Season03 145 2,412 655 10,060 6,520 5,996

Season04 141 1,790 1,848 8,870 5,580 5,272

Season05 85 1,685 528 7,410 4,900 4,373

Season06 62 1,700 100 5,760 1,880 2,588

Season07 127 2,132 485 11,000 7,540 6,805

Season08 120 4,409 3,550 18,300 8,875 10,022

ALL 1,290 2,928 100 18,300 5,490 5,630



### 1 3.7.2 Compliance with Limitations

EPA promulgates limitations that sites are ca pable of complying with at all times by properly operating and maintaini ng their processes and treatmen t technologies. However, the issue of exceedances or excursions (values that exceed the limitations) is often raised. In other rules, including EPA’s final OCPSF rule, commen ters suggested that EPA include a provision that a facility is in compliance with permit lim itations provided its discharge does not exceed the specified limitations, with the exception that the discharge may exceed the daily maximum limitation 1 day out of 100. EPA’s general approach in that case for developing limitations based on percentiles was the same as this rule and was upheld in Chemical Manufacturers Association v. U.S. Environmental Protection Agency, 870 F.2d 177, 230 (5th Cir. 1989). The Court determined the following:

EPA reasonably concluded that the da ta points exceeding the 99th and 95th percentiles represent either quality-contr ol problems or upsets because there can be no other explanation for these isolated and extremely high discharges. If these data points result from quality-control pr oblems, the exceedan ces they represent are within the control of the plant. If, however, the data points represent exceedances beyond the control of the industry, the upset defense is available. Id. at 230.

This issue also was raised in EPA’s Phase I rule for the Pulp, Paper, and Paperboard Category (USEPA, 1998). In that rulemaking, EPA used the same general percentile approach for developing monthly average limitations that it used for daily maximum limitation for the airport deicing rule. The percen tile approach for the monthly av erage limitation was upheld inTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

191 

### National Wildlife Federation et al. v. Environmental Protection Agency, 286 F.3d 554, 573 (D.C. Cir. 2002). The Court determined that:

EPA’s approach to developing monthly lim itations was reasonable. It established limitations based on percentiles achieved by facilities using well-operated and controlled processes and treatment systems. It is therefore reasonable for EPA to conclude that measurements above th e limitations are due to either upset conditions or deficiencies in process and treatment system maintenance and operation. EPA has included an affirmative defense that is available to mills that exceed limitations due to an unforeseen event. EPA reasonably concluded that other exceedances would be the result of design or operational deficiencies. EPA rejected Industry Petitioners’ claim th at facilities are expected to operate processes and treatment systems to violate the limitations at some pre-set rate. EPA explained that the statistical me thodology was used as a framework to establish the limitations based on percentiles. These limitations were never intended to have the rigid probabilistic in terpretation that Industry Petitioners have adopted. Therefore, we reject Industr y Petitioners’ challenge to the effluent limitations.

As that Court recognized, EP A’s allowance for reasonably an ticipated variability in its effluent limitations, coupled with the availability of the upset defense, reasonably accommodates acceptable excursions. Any further excursion allowances would go beyond the reasonable accommodation of variability and would jeopardize th e effective control of pollutant discharges on a consistent basis and/or bog down administra tive and enforcement proceedings in detailed fact-finding exercises, contrary to Congressional intent. See, for example, Rep. No. 92-414, 92d Congress, 2d Sess. 64, reprinted in A Legislative History of the Water Pollution Control Act Amendments of 1972 (at 1482); Legislative History of th e Clean Water Act of 1977 (at 464-65).

More recently, for EPA’s rule for the ir on and steel industry, EPA’s selection of percentiles was upheld in American Coke and Coal Chemicals Institute v. Environmental Protection Agency, 452 F.3d 930, 945 (D.C. Cir. 2006). The Court determined that:

The court will not second-guess EPA’s e xpertise with regard to what the maximum effluent limits represent. See Nat’l Wildlife , 286 F.3d at 571-73. As EPA explains in the Final Development Document, the daily and monthly average effluent limitations are not promulgated with the expectation that a plant will operate with an eye toward barely achi eving the limitations. Final Development Document at § 14.6.2. Should a plant do so, it could be expected to exceed these limits frequently because of the foreseeable variation in treatment effectiveness. Rather, the effluent limitations are promul gated with the expectation that plants will be operated with an eye towards ach ieving the equivalent of the long term average for the BAT-1 model technology. Id. However, even operated with the goal of achieving the BAT-1 long term average, a plant’s actual results will vary. EPA’s maximum daily limitations are de signed to be forgiving enough to cover the operations of a well-operated model facility 99% of the time, while its maximum monthly average limitations are designed to be forgiving enough to accommodate the operations of a well-opera ted model facility 95% of the time. See id. EPA’s choice of percentile distri bution represented by its maximumTechnical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

192 

### effluent limitation under the CWA represents an expert policy judgment that is not arbitrary or capricious.

EPA expects that airports will comply with promulgated limitations at all times. If an exceedance is caused by an upset condition, the ai rport would be able to defend against an enforcement action if it meets the requirements of 40 CFR 122.41(n). If the exceedance is caused by a design or operational deficiency, EPA has de termined that the airport’s performance does not represent the appropriate leve l of control (best av ailable technology for ex isting sources; best available demonstrated technology for new sources ). For promulgated limitations and standards, EPA has determined that such exceedances can be controlled by diligent process and wastewater treatment system operational practices such as fre quent inspection and repair of equipment, use of backup systems, and operator training and performance evaluations.

1 3.8 References

ERG. 2008. Personnel communication (email) between Mary Willett (ERG) and Mark Sober, Albany International Airport. (July 22). DCN AD00824.

ERG. 2008a. Email from Mark Sober (Albany Intern ational Airport) to Ma ry Willett (ERG). RE: One More Query. (July 22). DCN AD01206.

ERG. 2008b. Telecon between Cortney Itle (E RG) and Mark Sober (A lbany International Airport). RE: ALB Follow-up Qu estions. (August 14). DCN AD00825.

ERG. 2009. Memorandum from Mary Willett (ERG) to Brian D’Amico (EPA). Evaluation of Proposed Compliance Alternative Ammonia Lim itations with respect to Airport Deicing Stormwater Typical Ammonia Discharges. (June 30). DCN AD01194.

USEPA. 1987. Organic Chemicals and Plastics and Sy nthetic Fibers Category Effluent Limitations Guidelines, Pretre atment Standards and New Source Performance Standards; Final Rule. 40 CFR Part 414, 52 FR 42522, November 5, 1987.

USEPA. 1998. National Emission Standards for Hazardous Air Pollutants for Source Category: Pulp and Paper Production; Efflue nt Limitations Guidelines, Pretreatment Standards, and New Source Performance Standards: Pulp, Paper, and Paperboard Category; Final Rule. 40 CFR Part 430, 63 FR 18503, April 15, 1998.

USEPA. 2002. Development Document for Effluent Limitations Guidelines and Standards for the Iron and Steel Manufacturing Point Source Category . EPA-821-R-02-004. Section 14.1. Available online at www.epa.gov/guide/ironsteel/.

USEPA. 2006. Notice of Availability of Final 2006 Effluent Guidelines Program Plan. December 21, 2006; 71 FR 76655.

USEPA. 2010. Memorandum from Cuc Schroe der (EPA) to Brian D’Amico (EPA). Statistical Support Memorandum . (November). DCN AD01246.

Westat. 2009. Memorandum from John Roge rs (Westat) to Marla Smith (EPA). Calculation Percentiles . (June 8). DCN AD01213.Technical Development Document for Effluent Limitation Guidelines and Standard s for the Airport Deicing Category Section 13 – Limitations and Standard s: Data Selection and Calculation

193 

### Westat. 2009a. Memorandum from John Roge rs (Westat) to Marla Smith (EPA). Percentiles for Weekly Averages . (June 23). DCN AD01214.