Instructions for filling in the Emission Test Template

This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data fro

fuel burning power plants and which test methods were used to do so for cases where the test methods are not 

supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in t

if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 se

runs or sampling events for each of the requested constituents. This spreadsheet is intended to be used for one 

one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet.

yellow are required. All cells that are shaded in green are populated using drop-down lists. You do not need to 

cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. 

resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls 

(example: 8100_Unit_2_EmisTestMethods.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksh

2. Please enter the control device configuration.

Emission Data Worksheets

The emission data worksheets are provided for each constituent or constituent family required for this analysis. 

spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission 

results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or c

family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter bot

Hg+2, or if the Ontario-Hydro Method was used, you would need to enter Hg0, HgP, and Hg

Volatile Organic HAP and Speciated Semi-Volatile Organic HAP worksheets allow you to use a drop

Constituent field to define as many records as needed to record each HAP that you have results for. General ins

follow for these worksheets:

Boiler Operation Information

1. Please provide the values of all requested parameters for each of test run/sample.

2. Please provide any other supporting information or comments in the Other Supporting Information field.

Fuel Information

1. Please enter what types of fuel are being used in your boiler using the drop-downs in the Fuel Type Selection 

You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more sa

then enter an input rate of zero. 

2. Please enter the unit of measure using the drop down provided.

3. Please enter the test method used to determine the fuel input rate.

4. Please provide any other information that you feel may be important in the Other Supporting Information fie

Emission Data
1. Some constituents ask for the emission rate results of each run in two different units of measure, while other

If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) 

ppmvd @ 7% O2(parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both.

2. Please provide the test method used. This may or may not match the example given in the Test Method Used 

Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010).

3. Please provide any other information that you feel may be important in the Other Supporting Information fie

4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for p

enter these data.
nformation about emission data from fossil 

ses where the test methods are not currently 

nly be used if the method is not in the ERT or 

T. You must complete at least 3 separate 

sheet is intended to be used for one boiler of 

copies of this spreadsheet. Fields shaded in 

down lists. You do not need to populate 

rmation worksheet. Please name each 

nit_[BoilerID]_EmisTestMethods.xls 

ler on the Boiler Information worksheet. 

ent family required for this analysis. On each 

fuel input information, and emission test 

d depending on the constituent or constituent 

Mercury requires that you enter both Hg0 and 

, HgP, and Hg+2. However, both the Speciated 

low you to use a drop-down provided in the 

at you have results for. General instructions 

er Supporting Information field.

downs in the Fuel Type Selection field. 

fuel types entered in one or more samples, 

he Other Supporting Information field.
erent units of measure, while others do not. 

b/MMBtu (Pounds per million BTU) and 

, you are required to provide both.

mple given in the Test Method Used field. 

ethod (ex. U.S. EPA Method 0010).

he Other Supporting Information field.

 method you are entering data for please also 
EIA Facility Code Facility Name Boiler ID

2451 San Juan Unit 1
Control Device Configuraton

Listed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICR
lectronic ICR
EIA Facility Code Facility Name Boiler ID

2451 San Juan Unit 1

1 4/22/2010 13:10 4/22/2010 15:10

1 4/22/2010 13:10 4/22/2010 15:10

2 4/23/2010 7:58 4/23/2010 9:58

2 4/23/2010 7:58 4/23/2010 9:58

3 4/23/2010 14:18 4/23/2010 16:18

3 4/23/2010 14:18 4/23/2010 16:18

Run Number Test Start Date Test Start Time Test End Date Test End Time
Measured Value (μg/dscm) Basis (Wet or Dry) Test Method Used Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

0.106 Dry U.S. EPA Method 30B

0.106 Dry U.S. EPA Method 30B

0.096 Dry U.S. EPA Method 30B

0.114 Dry U.S. EPA Method 30B

0.113 Dry U.S. EPA Method 30B

0.124 Dry U.S. EPA Method 30B

Please note QA/QC documentation starting in Column "AI"

Total Vapor Phase Mercury Emission Test Results
(lb/mmBtu)

0.000000093 2192 3570 11.32 12.80

0.000000093 2192 3570 11.32 12.80

0.000000092 2212 3606 11.33 12.83

0.000000092 2212 3606 11.33 12.83

0.000000208 2212 3616 11.45 12.82

0.000000208 2212 3616 11.45 12.82

Flue Gas 

CO2 (%) Steam Output (1000 lb/hr) Total Heat Input (mmBtu/hr) Flue Gas Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

6.37 940740 120.1 354550 subbituminouslb/hour

6.37 940740 120.1 354550 subbituminouslb/hour

6.33 948006 120.1 354936 subbituminouslb/hour

6.33 948006 120.1 354936 subbituminouslb/hour

6.34 949743 120.5 360389 subbituminouslb/hour

6.34 949743 120.5 360389 subbituminouslb/hour

Flue Gas Temperature (F)

Fuel #1

Flue Gas 

O2 (%) Flue Gas Flow Rate (dscfm)
 QA/QC Documentation

Measurement 

Method Trap ID

Section 

1 Mass 

(ng)

Section 

2 Mass 

(ng)

Total 

Mass 

(ng)

Initial 

Spike 

(ng)

F-Factor 31559 57.4 0.5 57.9 50

F-Factor 31591 57.1 1 58.1 50

F-Factor 31571 56.7 0.5 57.2 50

F-Factor 31500 59.1 0.5 59.6 50

F-Factor 31121 56.7 0.5 57.2 50

F-Factor 31581 59.4 0.5 59.9 50

Other Supporting Information
Total NonSpike (ng)

Sample 

Volume 

(dscm)

Volume 

Difference (%) Volume Diff. Limit Breaktrough (%)

7.9 0.07849 0.871080139

8.1 0.07791 1.751313485

7.2 0.07916 0.881834215

9.6 0.07856 0.846023689

7.2 0.07823 0.881834215

9.9 0.07771 0.841750842

≤20% of field recovery test

Trap #1
Breaktrough Limit

≤ 10% of Section 1 Hg mass for Hg conc. >1 μg/dscm: or ≤ 20% of Section 1 for Hg conc.≤1 μg/dscm
Concentration 

(μg/dscm) Trap ID Section 1 Mass

Section 

2 Mass

Total 

Mass

Initial 

Spike

Total NonSpikeSample 

Volume

Volume 

Difference (%)

0.10065361 FGS01811 8.3 0.5 8.8 0 8.8 0.07832

0.10396078 FGS01601 7.9 0.5 8.4 0 8.4 0.07744

0.09095733 FGS01524 7.5 0.5 8 0 8 0.07905

0.12220115 FGS01803 7.8 0.5 8.3 0 8.3 0.07811

0.09203277 FGS01521 9.9 0.5 10.4 0 10.4 0.07815

0.12740165 FGS01887 8.9 0.5 9.4 0 9.4 0.0774
Volume Diff. Limit Breaktrough 

(%)

6.024096386

6.329113924

6.666666667

6.41025641

5.050505051

5.617977528

≤20% of field recovery test

Trap #2
Breaktrough Limit

Trap #2

≤ 10% of Section 1 Hg mass for Hg conc. >1 μg/dscm: or ≤ 20% of Section 1 for Hg conc.≤1 μg/dscm
Concentration 

(μg/dscm) Abs. diff. RD (%)

0.112353812 0.0117 5.4929

0.108472475 0.004512 2.1238

0.101206892 0.01025 5.3338

0.106257681 0.015943 6.9787

0.133077415 0.041045 18.233

0.121445459 0.005956 2.3935
Limit

Paired Trap Agreement (RD)

≥10 % RD mass for Hg conc. >1 μg/dscm: or ≤20% RD or ≤0.2 μg/dscm abs.diff. for Hg conc. ≤1 μg/dscm
Crec

R (%) by 

Run Ravg (%) Limit

49 98.2

49 98.3

49 98.5

51 102.5

47 93.7

51 101

Average Recovery, between 85 and 115%

Measured Spike Recovery ( R )

98.7
EIA Facility Code Facility Name Boiler ID

2451 San Juan Unit 1

1 4/22/2010 16:43 4/22/2010

2 4/23/2010 8:04 4/23/2010

3 4/23/2010 15:07 4/23/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used 

22:10 0.48 Dry U.S. EPA Conditional Test Method 033 (CTM-033)

14:42 0.26 Dry U.S. EPA Conditional Test Method 033 (CTM-033)

21:42 0.03 Dry U.S. EPA Conditional Test Method 033 (CTM-033)

Hydrogen Cyanide Emission Test Results

Test End Time
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

d 033 (CTM-033) 0.000482 2192 3529 15.4 12.6

d 033 (CTM-033) 0.000249 2212 3611 14.6 12.6

d 033 (CTM-033) Analysis was 0.000028 2212 3608 14.8 12.6

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Calculated 

Emission Rate 

(lb/mmBtu)

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

6.3 848161 116 356813 subbituminous lb/hour F-Factor

6.3 828448 116 359302 subbituminous lb/hour F-Factor

6.3 860111 116 365530 subbituminous lb/hour F-Factor

Flue Gas 

Temperature 

(F)

Fuel #1 Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)
Other Supporting Information
EIA Facility Code Facility Name Boiler ID

2451 San Juan Unit 1

1 4/22/2010 13:10

2 4/23/2010 7:58

3 4/23/2010 14:18

Run Number Test Start Date Test Start Time
Total Dissolved Solids 

(mg solids/liter)

Total Suspended Solids 

(mg solids/liter)

4/22/2010 15:10 51180 147752

4/23/2010 9:58 47020 127648

4/23/2010 16:18 46730.000 132444

Test End Date Test End Time
Test Method Used Data Flag (ADL, 

BDL, DDL)

Standard Test Method for Filterable and Nonfilterable Matter in Water ASTM D5907

Standard Test Method for Filterable and Nonfilterable Matter in Water ASTM D5907

Standard Test Method for Filterable and Nonfilterable Matter in Water ASTM D5907

Constisuent Emission Test Results
Test Method Comments Fuel Input Rate

2221 3570 940740 120.1 354550

2234 3606 948006 120.1 354936

2235 3616 949743 120.5 360389

Steam Output 

(1000 lb/hr)

Total Heat Input 

(mmBtu/hr)

Flue Gas 

Temperat

ure (F)

Flue Gas 

Flow Rate 

(dscfm)
Fuel Type Units of 

Measure

Measurement 

Method

bituminous lb/hour F-Factor

bituminous lb/hour F-Factor

bituminous lb/hour F-Factor

Other Supporting Information

Fuel #1