13339 Hagers Ferry Road

Huntersville, NC 28078-7929

McGuire Nuclear Complex - MG03A2

Phone: 980-875-5245 Fax: 980-875-4349

Order Summary Report

Analytical Laboratory

Order Number: J11010101

Project Name: WWTS - Biweekly

Lab Contact: Jason C Perkins

Date: 2/14/2011

Customer Address: 3195 Pine Hall Rd

Customer Name(s): Bill Kennedy, Melonie Martin, Wayne Chapman, Tom Johnson

Mailcode: Belews Steam Station

Belews Creek, NC 28012

Phone: 980-875-5348

Report Authorized By:

(Signature)

Program Comments:

FGD - Biweekly (1/17)

Data Flags & Calculations:

Any analytical tests or individual analytes within a test flagged with an "X" or "1" indicate a deviation from the method quality 

system or quality control requirement. All results are reported on a dry weight basis unless otherwise noted.

Data Package:

This data package includes analytical results that are applicable only to the samples described in this narrative. An estimation of 

the uncertainty of measurement for the results in the report is available upon request. This report shall not be reproduced, except 

in full, without the written consent of the Analytical Laboratory. Please contact the Analytical laboratory with any questions. The 

order of individual sections within this report is as follows:

Job Summary Report, Sample Identification, Technical Validation of Data Package, Analytical Laboratory Certificate of Analysis,

Analytical Laboratory QC Reports, Sub-contracted Laboratory Results, Customer Specific Data Sheets, Reports & 

Documentation, Customer Database Entries, Test Case Narratives, Chain of Custody (COC)

Certification:

The Analytical Laboratory holds the following State Certifications : North Carolina (DENR) Certificate #248, South Carolina 

(DHEC) Laboratory ID # 99005. Contact the Analytical Laboratory for definitive information about the certification status of 

specific methods. 

Analytical Laboratory 

Page 1 of 24
Sample ID's & Descriptions:

Sample ID Plant/Station

Collection 

Date and Time Collected By Sample Description

2011000396 BELEWS 17-Jan-11 1:05 AM ILLEGIBLE FGD Purge Eff 

2011000397 BELEWS 17-Jan-11 1:09 AM ILLEGIBLE EQ TANK EFF. 

2011000398 BELEWS 17-Jan-11 1:13 AM ILLEGIBLE BIOREACTOR 1 INF. 

2011000399 BELEWS 17-Jan-11 1:17 AM ILLEGIBLE BIOREACTOR 2 INF. 

2011000400 BELEWS 17-Jan-11 1:20 AM ILLEGIBLE BIOREACTOR 2 EFF. 

2011000401 BELEWS 17-Jan-11 Trip Blank 

2011000402 BELEWS 17-Jan-11 FILTER BLANK 

7 Total Samples

Analytical Laboratory 

Page 2 of 24
COC and .pdf report are in agreement with sample totals 

and analyses (compliance programs and procedures).

All Results are less than the laboratory reporting limits.

All laboratory QA/QC requirements are acceptable.

The Vendor Laboratories have been qualified by the 

Analytical Laboratory

Yes No

Technical Validation Review

Checklist:

Yes No

Yes No

Report Sections Included:

Job Summary Report Sub-contracted Laboratory Results

Sample Identification Customer Specific Data Sheets, Reports, & Documentation

Technical Validation of Data Package Customer Database Entries

Analytical Laboratory Certificate of Analysis Test Case Narratives

Analytical Laboratory QC Report Chain of Custody

Reviewed By: Jenny A Herman Date: 2/14/2011

Yes

Electronic Data Deliverable (EDD) Sent Separately

Analytical Laboratory 

Page 3 of 24
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J11010101

2011000396

Collection Date: 17-Jan-11 1:05 AM

Site: FGD Purge Eff 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

MERCURY (COLD VAPOR) IN WATER

Mercury (Hg) 235 ug/L EPA 245.1 20-Jan-11 14:45 5 TLINN

TOTAL RECOVERABLE METALS BY ICP

Aluminum (Al) 160 mg/L EPA 200.7 21-Jan-11 10:23 0.05 DJSULL1

Barium (Ba) 1.82 mg/L EPA 200.7 21-Jan-11 10:23 0.05 DJSULL1

Beryllium (Be) < 0.05 mg/L EPA 200.7 21-Jan-11 10:23 0.05 DJSULL1

Boron (B) 179 mg/L 0.5 EPA 200.7 21-Jan-11 10:23 DJSULL1

Calcium (Ca) 4090 mg/L 0.1 EPA 200.7 21-Jan-11 10:23 DJSULL1

Cobalt (Co) 0.181 mg/L 0.05 EPA 200.7 21-Jan-11 10:23 DJSULL1

Iron (Fe) 116 mg/L 0.1 EPA 200.7 21-Jan-11 10:23 DJSULL1

Magnesium (Mg) 687 mg/L 0.05 EPA 200.7 21-Jan-11 10:23 DJSULL1

Manganese (Mn) 6.42 mg/L 0.05 EPA 200.7 21-Jan-11 10:23 DJSULL1

Molybdenum (Mo) 0.102 mg/L 0.05 EPA 200.7 21-Jan-11 10:23 DJSULL1

Sodium (Na) 43.3 mg/L 0.5 EPA 200.7 21-Jan-11 10:23 DJSULL1

Tin (Sn) < 0.5 mg/L 0.5 EPA 200.7 21-Jan-11 10:23 DJSULL1

Titanium (Ti) 5.30 mg/L 0.05 EPA 200.7 21-Jan-11 10:23 DJSULL1

DISSOLVED METALS BY ICP-MS

Selenium (Se) 204 ug/L EPA 200.8 03-Feb-11 13:36 10 KRICHAR

TOTAL RECOVERABLE METALS BY ICP-MS

Antimony (Sb) < 100 ug/L EPA 200.8 09-Feb-11 11:48 100 KRICHAR

Arsenic (As) 423 ug/L EPA 200.8 09-Feb-11 11:48 100 KRICHAR

Cadmium (Cd) < 100 ug/L EPA 200.8 09-Feb-11 11:48 100 KRICHAR

Chromium (Cr) 351 ug/L 100 EPA 200.8 09-Feb-11 11:48 KRICHAR

Copper (Cu) 264 ug/L 100 EPA 200.8 09-Feb-11 11:48 KRICHAR

Lead (Pb) 391 ug/L 100 EPA 200.8 09-Feb-11 11:48 KRICHAR

Nickel (Ni) 278 ug/L 100 EPA 200.8 09-Feb-11 11:48 KRICHAR

Selenium (Se) 9300 ug/L 1000 EPA 200.8 09-Feb-11 11:48 KRICHAR

Silver (Ag) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:48 KRICHAR

Thallium (Tl) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:48 KRICHAR

Vanadium (V) 586 ug/L 100 EPA 200.8 09-Feb-11 11:48 KRICHAR

Zinc (Zn) 494 ug/L 200 EPA 200.8 09-Feb-11 11:48 KRICHAR

SELENIUM SPECIATION

Vendor Parameter Complete V_AS&C

TOTAL DISSOLVED SOLIDS

Vendor Parameter Complete V_PRISM

Analytical Laboratory 

Page 4 of 24
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J11010101

2011000397

Collection Date: 17-Jan-11 1:09 AM

Site: EQ TANK EFF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

MERCURY (COLD VAPOR) IN WATER

Mercury (Hg) 179 ug/L EPA 245.1 20-Jan-11 14:48 2.5 TLINN

TOTAL RECOVERABLE METALS BY ICP

Aluminum (Al) 156 mg/L EPA 200.7 21-Jan-11 10:27 0.05 DJSULL1

Barium (Ba) 1.75 mg/L EPA 200.7 21-Jan-11 10:27 0.05 DJSULL1

Beryllium (Be) < 0.05 mg/L EPA 200.7 21-Jan-11 10:27 0.05 DJSULL1

Boron (B) 190 mg/L 0.5 EPA 200.7 21-Jan-11 10:27 DJSULL1

Calcium (Ca) 4100 mg/L 0.1 EPA 200.7 21-Jan-11 10:27 DJSULL1

Cobalt (Co) 0.178 mg/L 0.05 EPA 200.7 21-Jan-11 10:27 DJSULL1

Iron (Fe) 109 mg/L 0.1 EPA 200.7 21-Jan-11 10:27 DJSULL1

Magnesium (Mg) 709 mg/L 0.05 EPA 200.7 21-Jan-11 10:27 DJSULL1

Manganese (Mn) 6.52 mg/L 0.05 EPA 200.7 21-Jan-11 10:27 DJSULL1

Molybdenum (Mo) 0.077 mg/L 0.05 EPA 200.7 21-Jan-11 10:27 DJSULL1

Sodium (Na) 45.1 mg/L 0.5 EPA 200.7 21-Jan-11 10:27 DJSULL1

Tin (Sn) < 0.5 mg/L 0.5 EPA 200.7 21-Jan-11 10:27 DJSULL1

Titanium (Ti) 5.10 mg/L 0.05 EPA 200.7 21-Jan-11 10:27 DJSULL1

DISSOLVED METALS BY ICP-MS

Selenium (Se) 145 ug/L EPA 200.8 03-Feb-11 13:40 10 KRICHAR

TOTAL RECOVERABLE METALS BY ICP-MS

Antimony (Sb) < 100 ug/L EPA 200.8 09-Feb-11 11:43 100 KRICHAR

Arsenic (As) 326 ug/L EPA 200.8 09-Feb-11 11:43 100 KRICHAR

Cadmium (Cd) < 100 ug/L EPA 200.8 09-Feb-11 11:43 100 KRICHAR

Chromium (Cr) 278 ug/L 100 EPA 200.8 09-Feb-11 11:43 KRICHAR

Copper (Cu) 321 ug/L 100 EPA 200.8 09-Feb-11 11:43 KRICHAR

Lead (Pb) 305 ug/L 100 EPA 200.8 09-Feb-11 11:43 KRICHAR

Nickel (Ni) 345 ug/L 100 EPA 200.8 09-Feb-11 11:43 KRICHAR

Selenium (Se) 7930 ug/L 1000 EPA 200.8 09-Feb-11 11:43 KRICHAR

Silver (Ag) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:43 KRICHAR

Thallium (Tl) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:43 KRICHAR

Vanadium (V) 468 ug/L 100 EPA 200.8 09-Feb-11 11:43 KRICHAR

Zinc (Zn) 614 ug/L 200 EPA 200.8 09-Feb-11 11:43 KRICHAR

2011000398

Collection Date: 17-Jan-11 1:13 AM

Site: BIOREACTOR 1 INF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

TOTAL RECOVERABLE METALS BY ICP

Aluminum (Al) 1.25 mg/L EPA 200.7 21-Jan-11 10:31 0.05 DJSULL1

Barium (Ba) 0.432 mg/L EPA 200.7 21-Jan-11 10:31 0.05 DJSULL1

Beryllium (Be) < 0.05 mg/L EPA 200.7 21-Jan-11 10:31 0.05 DJSULL1

Analytical Laboratory 

Page 5 of 24
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J11010101

2011000398

Collection Date: 17-Jan-11 1:13 AM

Site: BIOREACTOR 1 INF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

TOTAL RECOVERABLE METALS BY ICP

Boron (B) 184 mg/L EPA 200.7 21-Jan-11 10:31 0.5 DJSULL1

Calcium (Ca) 3700 mg/L EPA 200.7 21-Jan-11 10:31 0.1 DJSULL1

Cobalt (Co) < 0.05 mg/L EPA 200.7 21-Jan-11 10:31 0.05 DJSULL1

Iron (Fe) < 0.1 mg/L EPA 200.7 21-Jan-11 10:31 0.1 DJSULL1

Magnesium (Mg) 663 mg/L EPA 200.7 21-Jan-11 10:31 0.05 DJSULL1

Manganese (Mn) 2.70 mg/L EPA 200.7 21-Jan-11 10:31 0.05 DJSULL1

Molybdenum (Mo) < 0.05 mg/L EPA 200.7 21-Jan-11 10:31 0.05 DJSULL1

Sodium (Na) 42.9 mg/L EPA 200.7 21-Jan-11 10:31 0.5 DJSULL1

Tin (Sn) < 0.5 mg/L EPA 200.7 21-Jan-11 10:31 0.5 DJSULL1

Titanium (Ti) < 0.05 mg/L EPA 200.7 21-Jan-11 10:31 0.05 DJSULL1

DISSOLVED METALS BY ICP-MS

Selenium (Se) 85.6 ug/L EPA 200.8 03-Feb-11 13:43 10 KRICHAR

TOTAL RECOVERABLE METALS BY ICP-MS

Antimony (Sb) < 100 ug/L EPA 200.8 09-Feb-11 11:28 100 KRICHAR

Arsenic (As) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:28 KRICHAR

Cadmium (Cd) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:28 KRICHAR

Chromium (Cr) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:28 KRICHAR

Copper (Cu) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:28 KRICHAR

Lead (Pb) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:28 KRICHAR

Nickel (Ni) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:28 KRICHAR

Selenium (Se) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:28 KRICHAR

Silver (Ag) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:28 KRICHAR

Thallium (Tl) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:28 KRICHAR

Vanadium (V) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:28 KRICHAR

Zinc (Zn) < 200 ug/L 200 EPA 200.8 09-Feb-11 11:28 KRICHAR

SELENIUM SPECIATION

Vendor Parameter Complete V_AS&C

2011000399

Collection Date: 17-Jan-11 1:17 AM

Site: BIOREACTOR 2 INF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

TOTAL RECOVERABLE METALS BY ICP

Aluminum (Al) 1.29 mg/L EPA 200.7 21-Jan-11 10:35 0.05 DJSULL1

Barium (Ba) 0.459 mg/L 0.05 EPA 200.7 21-Jan-11 10:35 DJSULL1

Beryllium (Be) < 0.05 mg/L 0.05 EPA 200.7 21-Jan-11 10:35 DJSULL1

Boron (B) 184 mg/L 0.5 EPA 200.7 21-Jan-11 10:35 DJSULL1

Calcium (Ca) 3780 mg/L 0.1 EPA 200.7 21-Jan-11 10:35 DJSULL1

Cobalt (Co) < 0.05 mg/L 0.05 EPA 200.7 21-Jan-11 10:35 DJSULL1

Analytical Laboratory 

Page 6 of 24
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J11010101

2011000399

Collection Date: 17-Jan-11 1:17 AM

Site: BIOREACTOR 2 INF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

TOTAL RECOVERABLE METALS BY ICP

Iron (Fe) 0.385 mg/L EPA 200.7 21-Jan-11 10:35 0.1 DJSULL1

Magnesium (Mg) 693 mg/L EPA 200.7 21-Jan-11 10:35 0.05 DJSULL1

Manganese (Mn) 2.82 mg/L EPA 200.7 21-Jan-11 10:35 0.05 DJSULL1

Molybdenum (Mo) < 0.05 mg/L EPA 200.7 21-Jan-11 10:35 0.05 DJSULL1

Sodium (Na) 44.2 mg/L EPA 200.7 21-Jan-11 10:35 0.5 DJSULL1

Tin (Sn) < 0.5 mg/L EPA 200.7 21-Jan-11 10:35 0.5 DJSULL1

Titanium (Ti) < 0.05 mg/L EPA 200.7 21-Jan-11 10:35 0.05 DJSULL1

TOTAL RECOVERABLE METALS BY ICP-MS

Antimony (Sb) < 100 ug/L EPA 200.8 09-Feb-11 11:22 100 KRICHAR

Arsenic (As) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:22 KRICHAR

Cadmium (Cd) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:22 KRICHAR

Chromium (Cr) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:22 KRICHAR

Copper (Cu) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:22 KRICHAR

Lead (Pb) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:22 KRICHAR

Nickel (Ni) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:22 KRICHAR

Selenium (Se) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:22 KRICHAR

Silver (Ag) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:22 KRICHAR

Thallium (Tl) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:22 KRICHAR

Vanadium (V) < 100 ug/L 100 EPA 200.8 09-Feb-11 11:22 KRICHAR

Zinc (Zn) < 200 ug/L 200 EPA 200.8 09-Feb-11 11:22 KRICHAR

2011000400

Collection Date: 17-Jan-11 1:20 AM

Site: BIOREACTOR 2 EFF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

MERCURY (COLD VAPOR) IN WATER

Mercury (Hg) < 1 ug/L EPA 245.1 20-Jan-11 14:50 1 TLINN

TOTAL RECOVERABLE METALS BY ICP

Aluminum (Al) 1.29 mg/L EPA 200.7 21-Jan-11 10:39 0.05 DJSULL1

Barium (Ba) 0.436 mg/L 0.05 EPA 200.7 21-Jan-11 10:39 DJSULL1

Beryllium (Be) < 0.05 mg/L 0.05 EPA 200.7 21-Jan-11 10:39 DJSULL1

Boron (B) 173 mg/L 0.5 EPA 200.7 21-Jan-11 10:39 DJSULL1

Calcium (Ca) 3720 mg/L 0.1 EPA 200.7 21-Jan-11 10:39 DJSULL1

Cobalt (Co) < 0.05 mg/L 0.05 EPA 200.7 21-Jan-11 10:39 DJSULL1

Iron (Fe) 0.141 mg/L 0.1 EPA 200.7 21-Jan-11 10:39 DJSULL1

Magnesium (Mg) 693 mg/L 0.05 EPA 200.7 21-Jan-11 10:39 DJSULL1

Manganese (Mn) 2.63 mg/L 0.05 EPA 200.7 21-Jan-11 10:39 DJSULL1

Molybdenum (Mo) < 0.05 mg/L 0.05 EPA 200.7 21-Jan-11 10:39 DJSULL1

Sodium (Na) 43.9 mg/L 0.5 EPA 200.7 21-Jan-11 10:39 DJSULL1

Analytical Laboratory 

Page 7 of 24
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J11010101

2011000400

Collection Date: 17-Jan-11 1:20 AM

Site: BIOREACTOR 2 EFF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

TOTAL RECOVERABLE METALS BY ICP

Tin (Sn) < 0.5 mg/L EPA 200.7 21-Jan-11 10:39 0.5 DJSULL1

Titanium (Ti) < 0.05 mg/L EPA 200.7 21-Jan-11 10:39 0.05 DJSULL1

TOTAL RECOVERABLE METALS BY ICP-MS

Antimony (Sb) < 25 ug/L EPA 200.8 09-Feb-11 11:17 25 KRICHAR

Arsenic (As) < 25 ug/L 25 EPA 200.8 09-Feb-11 11:17 KRICHAR

Cadmium (Cd) < 25 ug/L 25 EPA 200.8 09-Feb-11 11:17 KRICHAR

Chromium (Cr) < 25 ug/L 25 EPA 200.8 09-Feb-11 11:17 KRICHAR

Copper (Cu) < 25 ug/L 25 EPA 200.8 09-Feb-11 11:17 KRICHAR

Lead (Pb) < 25 ug/L 25 EPA 200.8 09-Feb-11 11:17 KRICHAR

Nickel (Ni) < 25 ug/L 25 EPA 200.8 09-Feb-11 11:17 KRICHAR

Selenium (Se) < 25 ug/L 25 EPA 200.8 09-Feb-11 11:17 KRICHAR

Silver (Ag) < 25 ug/L 25 EPA 200.8 09-Feb-11 11:17 KRICHAR

Thallium (Tl) < 25 ug/L 25 EPA 200.8 09-Feb-11 11:17 KRICHAR

Vanadium (V) < 25 ug/L 25 EPA 200.8 09-Feb-11 11:17 KRICHAR

Zinc (Zn) < 50 ug/L 50 EPA 200.8 09-Feb-11 11:17 KRICHAR

SELENIUM SPECIATION

Vendor Parameter Complete V_AS&C

2011000401

Collection Date: 17-Jan-11

Site: Trip Blank 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

TOTAL RECOVERABLE METALS BY ICP

Aluminum (Al) < 0.005 mg/L EPA 200.7 21-Jan-11 10:03 0.005 DJSULL1

Barium (Ba) < 0.005 mg/L EPA 200.7 21-Jan-11 10:03 0.005 DJSULL1

Beryllium (Be) < 0.005 mg/L EPA 200.7 21-Jan-11 10:03 0.005 DJSULL1

Boron (B) < 0.05 mg/L 0.05 EPA 200.7 21-Jan-11 10:03 DJSULL1

Calcium (Ca) 0.019 mg/L 1 0.01 EPA 200.7 21-Jan-11 10:03 DJSULL1

Cobalt (Co) < 0.005 mg/L 0.005 EPA 200.7 21-Jan-11 10:03 DJSULL1

Iron (Fe) < 0.01 mg/L 0.01 EPA 200.7 21-Jan-11 10:03 DJSULL1

Magnesium (Mg) < 0.005 mg/L 0.005 EPA 200.7 21-Jan-11 10:03 DJSULL1

Manganese (Mn) < 0.005 mg/L 0.005 EPA 200.7 21-Jan-11 10:03 DJSULL1

Molybdenum (Mo) < 0.005 mg/L 0.005 EPA 200.7 21-Jan-11 10:03 DJSULL1

Sodium (Na) < 0.05 mg/L 0.05 EPA 200.7 21-Jan-11 10:03 DJSULL1

Tin (Sn) < 0.05 mg/L 0.05 EPA 200.7 21-Jan-11 10:03 DJSULL1

Titanium (Ti) < 0.005 mg/L 0.005 EPA 200.7 21-Jan-11 10:03 DJSULL1

TOTAL RECOVERABLE METALS BY ICP-MS

Antimony (Sb) < 1 ug/L EPA 200.8 09-Feb-11 11:12 1 KRICHAR

Arsenic (As) < 1 ug/L 1 EPA 200.8 09-Feb-11 11:12 KRICHAR

Analytical Laboratory 

Page 8 of 24
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J11010101

2011000401

Collection Date: 17-Jan-11

Site: Trip Blank 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

TOTAL RECOVERABLE METALS BY ICP-MS

Cadmium (Cd) < 1 ug/L EPA 200.8 09-Feb-11 11:12 1 KRICHAR

Chromium (Cr) < 1 ug/L EPA 200.8 09-Feb-11 11:12 1 KRICHAR

Copper (Cu) < 1 ug/L EPA 200.8 09-Feb-11 11:12 1 KRICHAR

Lead (Pb) < 1 ug/L EPA 200.8 09-Feb-11 11:12 1 KRICHAR

Nickel (Ni) < 1 ug/L EPA 200.8 09-Feb-11 11:12 1 KRICHAR

Selenium (Se) < 1 ug/L EPA 200.8 09-Feb-11 11:12 1 KRICHAR

Silver (Ag) < 1 ug/L EPA 200.8 09-Feb-11 11:12 1 KRICHAR

Thallium (Tl) < 1 ug/L EPA 200.8 09-Feb-11 11:12 1 KRICHAR

Vanadium (V) < 1 ug/L EPA 200.8 09-Feb-11 11:12 1 KRICHAR

Zinc (Zn) < 2 ug/L EPA 200.8 09-Feb-11 11:12 2 KRICHAR

SELENIUM SPECIATION

Vendor Parameter Complete V_AS&C

2011000402

Collection Date: 17-Jan-11

Site: FILTER BLANK 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

DISSOLVED METALS BY ICP-MS

Selenium (Se) < 2 ug/L EPA 200.8 03-Feb-11 13:46 2 KRICHAR

Analytical Laboratory 

Page 9 of 24
 

January 28, 2011 

Jay Perkins 

Duke Energy Analytical Laboratory 

Mail Code MGO3A2 (Building 7405) 

13339 Hagers Ferry Rd. 

Huntersville, NC 28078 

(704) 875-5245 

Project: Belews – FGD WWTS (2010, Bi-Weekly Sampling) (LIMS # J11010101) 

Dear Mr. Perkins, 

Attached is the report associated with four (4) aqueous samples submitted for selenium 

speciation analysis on January 20, 2011. The samples were received on January 21, 2011 

in a sealed cooler at -0.1o

C. Selenium speciation analysis was performed via ion 

chromatography inductively coupled plasma dynamic reaction cell mass spectrometry 

(IC-ICP-DRC-MS). Any analytical issues associated with the analysis are addressed in 

the following report. 

If you have any questions, please feel free to contact me at your convenience. 

 Sincerely, 

 

 Russell Gerads 

 Vice President 

 Applied Speciation and Consulting, LLC 

Analytical Laboratory 

Page 10 of 24
Applied Speciation and Consulting, LLC 

Report prepared for: 

Jay Perkins 

Duke Energy Analytical Laboratory 

Mail Code MGO3A2 (Building 7405) 

13339 Hagers Ferry Rd. 

Huntersville, NC 28078 

Project: Belews – FGD WWTS (2010, Bi-Weekly Sampling) (LIMS # J11010101) 

January 28, 2011 

1. Sample Reception 

Four (4) aqueous samples in 125mL HDPE bottles (provided by Applied Speciation 

and Consulting) were submitted for selenium speciation analysis on January 20, 2011. 

The samples were received on January 21, 2011 in a sealed container at -0.1o

C. 

The samples were received in a laminar flow clean hood void of trace metals 

contamination and ultra-violet radiation. Upon reception, the samples were 

designated discrete sample identifiers. An aliquot of each sample was filtered 

(0.45μm) and these filtrates were stored in a secure, monitored cryofreezer 

(maintained at a temperature of -80oC) until selenium speciation analysis could be 

performed via ion chromatography inductively coupled plasma dynamic reaction cell 

mass spectrometry (IC-ICP-DRC-MS). 

2. Sample Preparation 

All sample preparation is performed in laminar flow clean hoods known to be free 

from trace metals contamination. All applied water for dilutions and sample 

preservatives are monitored for contamination to account for any biases associated 

with the sample results. 

Selenium Speciation Analysis by IC-ICP-DRC-MS Prior to analysis, an aliquot of 

each sample was filtered with a syringe filter (0.45μm) and injected directly into a 

sealed autosampler vial. No further sample preparation was performed as any 

chemical alteration of the samples may shift the equilibrium of the system resulting in 

changes in speciation ratios. 

Analytical Laboratory 

Page 11 of 24
3. Sample Analysis 

All sample analysis is precluded by a minimum of a five-point calibration curve 

spanning the entire concentration range of interest. Calibration curves are performed 

at the beginning of each analytical day. All calibration curves, associated with each 

species of interest, are standardized by linear regression resulting in a response factor. 

All sample results are instrument blank corrected to account for any operational 

biases associated with the analytical platform. 

Prior to sample analysis, all calibration curves are verified using second source 

standards which are identified as initial calibration verification standards (ICV). 

Ongoing instrument performance is identified by the analysis of continuing 

calibration verification standards (CCV) and continuing calibration blanks (CCB) at a 

minimal interval of every ten analytical runs. 

Selenium Speciation Analysis by IC-ICP-DRC-MS All samples for selenium 

speciation analysis were analyzed by ion chromatography inductively coupled plasma 

dynamic reaction cell mass spectrometry (IC-ICP-DRC-MS) on January 24, 2010. 

An aliquot of each sample is injected onto an anion exchange column and mobilized 

by a basic (pH > 7) gradient. The eluting selenium species are then introduced into a 

radio frequency (RF) plasma where energy-transfer processes cause desolvation, 

atomization, and ionization. The ions are extracted from the plasma through a 

differentially-pumped vacuum interface and travel through a pressurized chamber 

(DRC) containing a specific reactive gas which preferentially reacts with interfering 

ions of the same target mass to charge ratios (m/z). A solid-state detector detects ions 

transmitted through the mass analyzer and the resulting current is processed by a data 

handling system. 

Retention times for each eluting species are compared to known standards for species 

identification. 

4. Analytical Issues 

The overall analyses went very well and no analytical issues were encountered. All 

quality control parameters associated with these samples were within acceptance 

limits. 

The estimated method detection limits (eMDLs) for selenite, selenate, and 

selenocyanate are generated from replicate analyses of the lowest standard in the 

calibration curve. Not all selenium species are present in preparation blanks; 

therefore, eMDL calculations based on preparation blanks are artificially biased low. 

The eMDL for methylseleninic acid and selenomethionine is calculated from the 

average eMDL of selenite, selenate, and selenocyanate. The calibration does not 

contain methylseleninic acid or selenomethionine due to impurities in these standards 

which would bias the results for other selenium species. 

Analytical Laboratory 

Page 12 of 24
If you have any questions or concerns regarding this report, please feel free to contact 

me. 

Sincerely, 

Russell Gerads 

Vice President 

Applied Speciation and Consulting, LLC 

Analytical Laboratory 

Page 13 of 24
Sample Results

Sample ID Se(IV) Se(VI) SeCN MeSe(IV) SeMe

Unkn

Spec

FGD Purge Eff 94.2 81.2 ND (<1.5) ND (<2.0) ND (<2.0) 0 

BioReactor 1 Inf 1.74 70.0 ND (<0.36) 0.77 ND (<0.50) 0 BioReactor 2 Eff ND (<0.61) ND (<0.53) ND (<0.36) ND (<0.50) ND (<0.50) 0 Metals Trip Blk ND (<0.12) ND (<0.11) ND (<0.073) ND (<0.10) ND (<0.10) 0 All results reflect the applied dilution and are reported in μg/LND = Not detected at the applied dilutionSeCN = SelenocyanateMeSe(IV) = Methylseleninic acidSeMe = SelenomethionineUnknown Se Species = Total concentration of all unknown Se species observed by IC-ICP-MSn = number of unknown Se species observed

Report Generated by: Russell Gerads

Applied Speciation and Consulting, LLC

Selenium Speciation Results for Duke Energy

Project Name: Belews - FGD WWTS (2010, Bi-Weekly Sampling)

Contact: Jay Perkins

Date: January 28, 2011

LIMS #J11010101
Quality Control Summary - Preparation Blank Summary

Analyte (μg/L) PBW1 PBW2 PBW3 PBW4 Mean StdDev eMDL* eMDL 10x eMSe(IV) 0.000 0.000 0.000 0.000 0.000 0.000 0.012 0.12 Se(VI) 0.000 0.000 0.000 0.000 0.000 0.000 0.011 0.11 SeCN 0.000 0.000 0.000 0.000 0.000 0.000 0.007 0.073 MeSe(IV) 0.000 0.000 0.000 0.000 0.000 0.000 0.010 0.10 SeMe 0.000 0.000 0.000 0.000 0.000 0.000 0.010 0.10 eMDL = Estimated Method Detection Limit*Please see narrative regarding eMDL calculationsQuality Control Summary - Certified Reference MaterialsAnalyte (μg/L) CRM True Value Result RecoverySe(IV) ICV 9.57 9.40 98.2Se(VI) ICV 9.48 9.12 96.2SeCN ICV 8.92 8.72 97.8MeSe(IV) ICV 6.47 5.48 84.7SeMe ICV 9.32 8.60 92.3

LIMS #J11010101

Date: January 28, 2011

Report Generated by: Russell Gerads

Applied Speciation and Consulting, LLC

Selenium Speciation Results for Duke Energy

Project Name: Belews - FGD WWTS (2010, Bi-Weekly Sampling)

Contact: Jay Perkins
Quality Control Summary - Matrix Duplicates

Analyte (μg/L) Sample ID Rep 1 Rep 2 Mean RPDSe(IV) Batch QC 744.5 748.7 746.6 0.6Se(VI) Batch QC 106.5 104.5 105.5 1.9SeCN Batch QC ND (<1.5) ND (<1.5) NC NCMeSe(IV) Batch QC 2.8 2.5 2.6 11.7SeMe Batch QC ND (<2.0) ND (<2.0) NC NCND = Not detected at the applied dilutionNC = Value was not calculated due to one or more concentrations below the eMDL Quality Control Summary - Matrix Spike/ Matrix Spike DuplicateAnalyte (μg/L) Sample ID Spike Conc MS Result Recovery Spike Conc MSD Result Recovery RPDSe(IV) Batch QC 1112 1825 97.0 1112 1871 101.1 2.5Se(VI) Batch QC 1009 1002 88.8 1009 1019 90.6 1.7SeCN Batch QC 915.0 761.0 83.2 915.0 736.9 80.5 3.2

LIMS #J11010101

Date: January 28, 2011

Report Generated by: Russell Gerads

Applied Speciation and Consulting, LLC

Selenium Speciation Results for Duke Energy

Project Name: Belews - FGD WWTS (2010, Bi-Weekly Sampling)

Contact: Jay Perkins
Analytical Laboratory 

Page 17 of 24
This data package contains the analytical results for the project identified above and includes a Case Narrative, Sample 

Results and Chain of Custody. Unless otherwise noted, all samples were received in acceptable condition and processed 

according to the referenced methods. 

Data qualifiers are flagged individually on each sample. A key reference for the data qualifiers appears at the end of this case 

narrative.

NC Certification No. 402

SC Certification No. 99012

NC Drinking Water Cert No. 37735

Case Narrative

01/27/2011

Duke Energy Corporation

Jay Perkins

13339 Hagers Ferry Road

Huntersville, NC 28078

Project: Belews - FGD WWTS (Bi-Weekly Sampling)

Project No.: J11010101

Lab Submittal Date: 01/18/2011

Prism Work Order: 1010336

Please call if you have any questions relating to this analytical report.

Respectfully,

PRISM LABORATORIES, INC.

VP Laboratory Services Reviewed By

Data Qualifiers Key Reference:

MDL Method Detection Limit

BRL Below Reporting Limit

RPD Relative Percent Difference

*

Results reported to the reporting limit. All other results are reported to the MDL with values between MDL and 

reporting limit indicated with a J.

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543

Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 Page 1 of 5

Analytical Laboratory 

Page 18 of 24
Sample Receipt Summary

01/27/2011

Prism Work Order: 1010336

Client Sample ID Lab Sample ID Matrix Date Sampled Date Received

2011000396/FGD Purge EFF 1010336-01 Water 01/17/11 01/18/11

Samples received in good condition at 2.1 degrees C unless otherwise noted.

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543

Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 Page 2 of 5

Analytical Laboratory 

Page 19 of 24
Laboratory Report

01/27/2011

Parameter Result Batch

ID

Report

Limit

Analysis

Date/Time

Dilution Method

Factor

Units MDL Analyst

13339 Hagers Ferry Road Project No.: J11010101

Project: Belews - FGD WWTS 

(Bi-Weekly Sampling)

Duke Energy Corporation

Huntersville, NC 28078

Attn: Jay Perkins

Sample Matrix: Water

Client Sample ID: 2011000396/FGD Purge E

Prism Sample ID: 1010336-01

Prism Work Order: 1010336

Time Collected: 01/17/11 13:05

Time Submitted: 01/18/11 16:00

General Chemistry Parameters

Total Dissolved Solids 15000 mg/L 50 8.7 1 *SM2540 C 1/21/11 14:00 JAB P1A0365

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543

Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 Page 3 of 5

Analytical Laboratory 

Page 20 of 24
1/27/11

Level II QC Report

13339 Hagers Ferry Road Project No: J11010101

Project: Belews - FGD WWTS 

(Bi-Weekly Sampling)

Duke Energy Corporation

Huntersville, NC 28078

Attn: Jay Perkins

Prism Work Order: 1010336

Time Submitted: 1/18/11 4:00:00PM

Result Limit

Reporting

Units Level

Spike

Result

Source

%REC

%REC

Limits RPD

RPD

 Analyte Limit Notes 

General Chemistry Parameters - Quality Control

Batch P1A0365 - NO PREP

Blank (P1A0365-BLK1) Prepared & Analyzed: 01/21/11 

Total Dissolved Solids BRL 50 mg/L

LCS (P1A0365-BS1) Prepared & Analyzed: 01/21/11 

Total Dissolved Solids 980 50 mg/L 1000 98 90-110

Duplicate (P1A0365-DUP1) Source: 1010336-01 Prepared & Analyzed: 01/21/11 

Total Dissolved Solids 15200 50 mg/L 14900 2 20

Sample Extraction Data

NO PREP

Lab Number Batch Initial Final Date

1010336-01 P1A0365 50 mL 50 mL 01/21/11

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543

Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 Page 4 of 5

Analytical Laboratory 

Page 21 of 24

Analytical Laboratory 

Page 23 of 24
Analytical Laboratory 

Page 24 of 24