### Instructions for filling in the Emission Test Template

This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate runs or sampling events for each of the requested constituents. This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. yellow are required. All cells that are shaded in green are populated using drop

- down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls (example: 8100_Unit_2_EmisTestMethods.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet. 2. Please enter the control device configuration.

Emission Data Worksheets

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg Hg+2

### , or if the Ontario

- Hydro Method was used, you would need to enter Hg0

### , HgP, and Hg Volatile Organic HAP and Speciated Semi

-Volatile Organic HAP worksheets allow you to use a drop Constituent field to define as many records as needed to record each HAP that you have results for. General instructions follow for these worksheets:

Boiler Operation Information

1. Please provide the values of all requested parameters for each of test run/sample. 2. Please provide any other supporting information or comments in the Other Supporting Information field.

Fuel Information

1. Please enter what types of fuel are being used in your boiler using the drop

- downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples, then enter an input rate of zero. 2. Please enter the unit of measure using the drop down provided. 3. Please enter the test method used to determine the fuel input rate. 4. Please provide any other information that you feel may be important in the Other Supporting Information field.

Emission Data

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and ppmvd @ 7% O 2 

### (parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please also enter these data.

### This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. Fields shaded in down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet.

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg0 

### and , HgP, and Hg+2 

### . However, both the Speciated Volatile Organic HAP worksheets allow you to use a drop

- down provided in the Constituent field to define as many records as needed to record each HAP that you have results for. General instructions

2. Please provide any other supporting information or comments in the Other Supporting Information field.

downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples,

4. Please provide any other information that you feel may be important in the Other Supporting Information field.

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and

(parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please alsoEIA

Facility Code Facility Name Boiler ID

2451 San Juan Unit 1Control Device Configuraton

Listed (by

boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICRListed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICREIA

Facility Code Facility Name Boiler ID

2451 San Juan Unit 1

1 4/22/2010 13:10 4/22/2010 15:10 1 4/22/2010 13:10 4/22/2010 15:10 2 4/23/2010 7:58 4/23/2010 9:58 2 4/23/2010 7:58 4/23/2010 9:58 3 4/23/2010 14:18 4/23/2010 16:18 3 4/23/2010 14:18 4/23/2010 16:18 Run Number Test Start Date Test Start Time Test End Time Test End DateMeasured Value (μg/dscm) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) Test Method

Comments
0.106 Dry U.S. EPA Method 30B 0.106 Dry U.S. EPA Method 30B 0.096 Dry U.S. EPA Method 30B 0.114 Dry U.S. EPA Method 30B 0.113 Dry U.S. EPA Method 30B 0.124 Dry U.S. EPA Method 30B Please note QA/QC documentation starting in Column "AI"

Total Vapor Phase Mercury Emission Test Results(lb/mmBtu)

0.000000093 2192 3570 11.32 12.80 0.000000093 2192 3570 11.32 12.80 0.000000092 2212 3606 11.33 12.83 0.000000092 2212 3606 11.33 12.83 0.000000208 2212 3616 11.45 12.82 0.000000208 2212 3616 11.45 12.82 Flue Gas CO 2(%) Flue Gas Moisture (%) Steam Output (1000 lb/hr) Total Heat Input (mmBtu/hr)Fuel Input Rate Fuel Type Units of

Measure
6.37 940740 120.1 354550 subbituminous lb/hour 6.37 940740 120.1 354550 subbituminous lb/hour 6.33 948006 120.1 354936 subbituminous lb/hour 6.33 948006 120.1 354936 subbituminous lb/hour 6.34 949743 120.5 360389 subbituminous lb/hour 6.34 949743 120.5 360389 subbituminous lb/hour Flue Gas Temperature (F) Fuel #1 Flue Gas O 2(%) Flue Gas Flow Rate (dscfm)QA /QC Documentation

Measurement Method Trap ID Section 1 Mass (ng) Section 2 Mass (ng) Total Mass (ng) Initial Spike (ng) F-Factor 31559 57.4 0.5 57.9 50 F-Factor 31591 57.1 1 58.1 50 F-Factor 31571 56.7 0.5 57.2 50 F-Factor 31500 59.1 0.5 59.6 50 F-Factor 31121 56.7 0.5 57.2 50 F-Factor 31581 59.4 0.5 59.9 50

Other Supporting InformationTotal NonSpike (ng) Sample

Volume (dscm) Volume

Difference (%) Volume Diff. Limit Breaktrough (%)
7.9 0.07849 0.871080139 8.1 0.07791 1.751313485 7.2 0.07916 0.881834215 9.6 0.07856 0.846023689 7.2 0.07823 0.881834215 9.9 0.07771 0.841750842 ≤20% of field recovery

test Trap #1Breaktrough Limit

≤10% of Section 1 Hg mass for Hg conc. >1 μg/dscm: or ≤20% of Section 1 for Hg conc. ≤1 μg/dscmConcentration

(μg/dscm) Trap ID Section 1 Mass Section

2 Mass Total

Mass Initial Spike Total NonSpike Sample

Volume Volume

Difference (%)
0.10065361 FGS01811 8.3 0.5 8.8 0 8.8 0.07832 0.10396078 FGS01601 7.9 0.5 8.4 0 8.4 0.07744 0.09095733 FGS01524 7.5 0.5 8 0 8 0.07905 0.12220115 FGS01803 7.8 0.5 8.3 0 8.3 0.07811 0.09203277 FGS01521 9.9 0.5 10.4 0 10.4 0.07815 0.12740165 FGS01887 8.9 0.5 9.4 0 9.4 0.0774Volume Diff. Limit Breaktrough (%)
6.024096386 6.329113924 6.666666667 6.41025641 5.050505051 5.617977528 ≤20% of field recovery

test Trap #2Breaktrough Limit Trap #2

≤10% of Section 1 Hg mass for Hg conc. >1 μg/dscm: or ≤20% of Section 1 for Hg conc. ≤1 μg/dscmConcentration

(μg/dscm) Abs. diff. RD (%)

0.112353812 0.0117 5.4929 0.108472475 0.004512 2.1238 0.101206892 0.01025 5.3338 0.106257681 0.015943 6.9787 0.133077415 0.041045 18.233 0.121445459 0.005956 2.3935Limit Paired Trap Agreement (RD)

≥ 10 % RD mass for Hg conc. >1 μg/dscm: or ≤20% RD or ≤ 0.2 μg/dscm abs.diff. for Hg conc. ≤1μg/dscmC rec R (%) by

Run Ravg(%) Limit

49 98.2 49 98.3 49 98.5 51 102.5 47 93.7 51 101 Average Recovery, between 85 and 115%

Measured Spike Recovery ( R )

98.7EIA

Facility Code Facility Name Boiler ID

2451 San Juan Unit 1

1 4/22/2010 16:43 4/22/2010 2 4/23/2010 8:04 4/23/2010 3 4/23/2010 15:07 4/23/2010 Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry) Test Method Used
22:10 0.48 Dry U.S. EPA Conditional Test Method 033 (CTM-033) 14:42 0.26 Dry U.S. EPA Conditional Test Method 033 (CTM-033) 21:42 0.03 Dry U.S. EPA Conditional Test Method 033 (CTM-033) Hydrogen Cyanide Emission Test Results Test End TimeData Flag (ADL,

BDL, DDL) Test Method

Comments U.S. EPA Conditional Test Method 033 (CTM-033) 0.000482 2192 3529 15.4 12.6 U.S. EPA Conditional Test Method 033 (CTM-033) 0.000249 2212 3611 14.6 12.6 U.S. EPA Conditional Test Method 033 (CTM-033) Analysis was 0.000028 2212 3608 14.8 12.6 Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr) Calculated Emission Rate (lb/mmBtu) Flue Gas Moisture (%) Flue Gas CO 2(%)Fuel Input Rate Fuel Type Units of Measure Measurement

Method 6.3 848161 116 356813 subbituminous lb/hour F-Factor 6.3 828448 116 359302 subbituminous lb/hour F-Factor 6.3 860111 116 365530 subbituminous lb/hour F-Factor Flue Gas Temperature (F) Fuel #1 Flue Gas O 2(%) Flue Gas

Flow Rate (dscfm)Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 2451 San Juan Unit 1

1 4/22/2010 13:10 2 4/23/2010 7:58 3 4/23/2010 14:18 Run Number Test Start Date Test Start TimeTotal Dissolved Solids (mg solids/liter) Total Suspended Solids (mg solids/liter)
4/22/2010 15:10 51180 147752 4/23/2010 9:58 47020 127648 4/23/2010 16:18 46730.000 132444

Test End Time Test End DateTest Method Used Data Flag (ADL, BDL, DDL)
Standard Test Method for Filterable and Nonfilterable Matter in W ater ASTM D5907 Standard Test Method for Filterable and Nonfilterable Matter in W ater ASTM D5907 Standard Test Method for Filterable and Nonfilterable Matter in W ater ASTM D5907 Constisuent Emission Test ResultsTest Method Comments Fuel Input Rate

2221 3570 940740 120.1 354550 2234 3606 948006 120.1 354936 2235 3616 949743 120.5 360389 Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr) Flue Gas Temperat ure (F) Flue Gas Flow Rate (dscfm)Fuel Type Units of Measure Measurement

Method
bitum inous lb/hour F-Factor bitum inous lb/hour F-Factor bitum inous lb/hour F-Factor Other Supporting Information Fuel #1