Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Information Collection Request Emission Test Program Report

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Monday, November 21, 2011 Page 1 of 10
Information Collection Request Emission Test Program Report

Facility Information:

Cleco Power, LLC

275 Rodamacher Road

Lena LA 71447

Contact: Paul Turregano

Phone: 318 484-7413

Fax:

Email: paul.turregano@cleco.com

Testing Company:

Shaw E & I

4171 Essen Lane

Baton Rouge LA 70809

Contact:Richard Ishikawa

Phone: 225 932-2745

Fax:

Email: richard.ishikawa@shawgrp.com

Air Permit Number: Permitted Source ID/Name:

7446811 Cleco Rodemacher Power Station

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rat

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information:

AFS #: FRS #:

SCC / Description

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Boiler 31 216 0 0 0 4.5 12.5 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Boiler 31 Carbon Monoxide Method 10 2 120 0

Boiler 31 Co2 Method 3A CO2 3 60 0

Boiler 31 O2 Method 3A O2 3 60 0

Regulation Description Compound Limit Unit

EPA's Information Collection Request for electric utility 

steam generating units

0

Monday, November 21, 2011 Page 2 of 10
Information Collection Request Emission Test Program Report The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Monday, November 21, 2011 Page 3 of 10
Information Collection Request Emission Test Program Report

Sampling / Stack Data Results Summary

Location Boiler 31 - Method 10

Average

Run Number 1 2

Test Date 2/15/2011 2/15/2011

Run Start Time 10:00:00 AM 12:55:00 

PM

Run Finish Time 12:38:00 PM 3:45:00 PM

Carbon Dioxide, % 14.59 14.39 14.490

Oxygen, % 5.44 5.68 5.560

Dry Volumetric Flow Rate, dry scfm 685683 714268 699,975.500

F-Factor, dscfm/MMBtu @ %O2 9937 9888 9,912.500

Moisture, % 0 0 0.000

Fuel Type Override Override

Fw 0 0 0.000

Fc 0 0 0.000

Location Boiler 31 - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, November 21, 2011 Page 4 of 10
Information Collection Request Emission Test Program Report

Location Boiler 31 - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, November 21, 2011 Page 5 of 10
Information Collection Request Emission Test Program Report

Emissions Summary

Location: Boiler 31 - Method 10

Compound: Carbon Monoxide

Average

Run 1 2

Elb/hr 4.14E+01 4.62E+01 43.800

lb/mmBtuO2 1.35E-02 1.47E-02 0.014

ppm 1.38E+01 1.48E+01 14.300

ppm@7%O2 1.24E+01 1.35E+01 12.950

Monday, November 21, 2011 Page 6 of 10
Information Collection Request Emission Test Program Report

Process Run Data

APCD Run Data

Process Lab Run Data

Monday, November 21, 2011 Page 7 of 10
Information Collection Request Emission Test Program Report

Sampling / Stack Data Results Detail

Location Boiler 31 - Method 10

Average

Run Number 1 2

Test Date 2/15/2011 2/15/2011

Run Start Time 10:00:00 AM 12:55:00 PM

Run Finish Time 12:38:00 PM 3:45:00 PM

Carbon Dioxide, % 14.59 14.39 14.490

Oxygen, % 5.44 5.68 5.560

Fuel Factor 1.06 1.06

Dry Volumetric Flow Rate, dry scfm 685683 714268 699,975.500

F-Factor, dscfm/MMBtu @ %O2 9937 9888 9,912.500

Moisture, % 0 0 0.000

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range 95.05 95.09 95.070

Operating Units ppm pmm

No. Readings/Avg. 30 30 30.000

Calibration Set 1 1 1.000

Calibration Pre Zero Cylinder ID UHP UHP

Calibration Pre Zero Cylinder Instrument Response -1.05 -0.55 -0.800

Calibration Pre Zero Cylinder Bias -1.1 -0.58 -0.840

Calibration Pre Zero Cylinder Drift 0 0 0.000

Calibration Pre High Cylinder ID SG9160615B

AL

SG9160615B

AL

Calibration Pre High Cylinder Instrument Response 49.28 50.35 49.815

Calibration Pre High Cylinder Bias -0.44 0.68 0.120

Calibration Pre High Cylinder Drift 0 0 0.000

Calibration Post Zero Cylinder ID UHP UHP

Calibration Post Zero Cylinder Instrument Response -0.55 0.04 -0.255

Calibration Post Zero Cylinder Bias -0.58 0.04 -0.270

Calibration Post Zero Cylinder Drift 0.52 0.62 0.570

Calibration Post High Cylinder ID SG9160615B

AL

SG9160615B

AL

Calibration Post High Cylinder Instrument Response 50.35 50.11 50.230

Calibration Post High Cylinder Bias 0.68 0.43 0.555

Calibration Post High Cylinder Drift 1.12 0.25 0.685

Cavg 13 14.5 13.750

Cavg Units ppmvd ppmvd

Cgas 13.8477 14.8441 14.346

Cgas Units ppmvd ppmvd

Fuel Type Override Override

Fw 0 0 0.000

Fc 0 0 0.000

Cgasw 0 0 0.000

Cgasw Units

Monday, November 21, 2011 Page 8 of 10
Information Collection Request Emission Test Program Report

Location Boiler 31 - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 9 of 10
Information Collection Request Emission Test Program Report

Location Boiler 31 - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 10 of 10