Index | Site       Map | FAQ | Facility       Info | Reading       Rm | New | Help | Glossary | Contact UsProtecting People and the EnvironmentUNITED STATES NUCLEAR REGULATORY COMMISSION -   About NRC    - The     Commission 
  - Statutory Authority 
  - Strategic Plan 
  - Budget &      Performance 
  - Organization & Functions 
  - Locations 
  - History 
  - Values 
  - Policymaking 
  - Radiation Protection 
  - Fire Protection 
  - How We Regulate 
  - Grants 
  - Civil Rights 
  - 
- NuclearReactors    - Operating Reactor Locations 
  - Reactor Quick Links 
  - Power Reactors 
  - Research and Test     Reactors 
  - Operating Reactors 
  - Operator Licensing 
  - New Reactors 
  - Operator     Licensing for New Reactors 
  - Reactor Safety Research 
  - Advisory Comm (ACRS) 
  - Decommissioning     of Nuclear Facilities 
  - 
- NuclearMaterials    - Fuel Cycle Facility Locations 
  - Uranium     Recovery Locations 
  - Materials Quick Links 
  - Special Nuclear Material 
  - Source Material 
  - Byproduct Material 
  - Med, Academic & Ind Uses 
  - Source Materials Facilities 
  - Uranium Recovery 
  - Fuel Cycle Facilities 
  - Materials     Transportation 
  - Materials Research 
  - Advisory Comm (ACMUI) 
  - Decommissioning     of Nuclear Facilities 
  - Materials     Environmental Reviews 
  - 
- RadioactiveWaste    - Waste Quick Links 
  - Low-Level Waste 
  - Waste Incidental to     Reprocessing 
  - Incidental Waste Criteria 
  - High-Level Waste 
  - Uranium Mill Tailings 
  - LLW Disposal 
  - HLW Disposal 
  - Spent Fuel Storage 
  - Spent Fuel Transport 
  - Waste Research 
  - 
- NuclearSecurity    - Security     Spotlight 
  - NRC     Responsibilities 
  - Domestic Safeguards 
  - Radioactive Material Security 
  - Facility Protection 
  - Nuclear Material Control 
  - International Safeguards 
  - Information Security 
  - Emergency     Preparedness 
  - &; 
- Public Meetings&   Involvement    - Public Meeting Schedule 
  - Commission     Schedule 
  - Conferences & Symposia 
  - Documents for Comment 
  - Brochures & Fact Sheets 
  - Involving Stakeholders 
  - Info Quality Guidelines 
  - Rulemaking Process 
  - Licensing 
  - Enforcement 
  - Hearing Process 
  - Hearing Applications 
  - 

Home       > Electronic Reading       Room       > Document       Collections       > General       Communications       > Information       Notices       > 2000       > IN 2000-09

UNITED STATESNUCLEAR REGULATORY COMMISSIONOFFICE OF NUCLEAR REACTOR REGULATIONWASHINGTON, D.C. 20555-0001

June 28, 2000
NRC INFORMATION NOTICE 2000-09:STEAM GENERATOR TUBE FAILURE AT INDIAN POINT UNIT 2- Addressees 
- Purpose 
- Description   of Circumstances 
- Discussion 
- Operator   Performance 
- Procedure   Quality 
- Equipment   Performance 
- Emergency   Response 
Addressees
All holders of operating licenses for nuclear power reactors except those who have ceased operations and have certified that fuel has been permanently removed from the reactor vessel.
Purpose
The U.S. Nuclear Regulatory Commission (NRC) is issuing this information notice to inform addressees of a steam generator tube failure at Indian Point Unit 2. NRC investigations of the licensee's steam generator inspection program are ongoing and any potentially generic issues identified will be communicated in a separate generic communication. However, the investigations to date re-emphasize the importance of licensee involvement with ongoing industry efforts to understand and detect steam generator degradation. It is expected that recipients will review the information for applicability to their facilities and consider actions, as appropriate, to avoid similar problems. However, suggestions contained in this information notice are not NRC requirements; therefore, no specific action or written response is required.
Description of Circumstances
On February 15, 2000, at 7:17 p.m., the Indian Point Unit 2 nuclear plant experienced a steam generator tube failure, which required the declaration of an Alert at 7:29 p.m., and a manual reactor trip at 7:30 p.m. The operators identified that the #24 steam generator was the source of the leak and completed isolation of the #24 steam generator by 8:31 p.m.

At 9:02 p.m., the operator opened the high-pressure steam dump valves and established an excessive primary plant cooldown rate that caused a rapid reduction in the pressurizer level and required the operators to manually initiate safety injection. The operators reset the safety injection at 9:21 p.m., reduced the reactor coolant system pressure to about 970 psig at 9:32 p.m., and re-commenced a plant cooldown at 11:35 p.m.

The residual heat removal (RHR) system was placed in service on February 16, 2000, at 12:38 p.m., and primary plant pressure was reduced below the #24 steam generator pressure to terminate the steam generator tube leakage at 2:20 p.m. The plant cooldown continued, and the plant entered cold shutdown at 4:57 p.m. The licensee exited the Alert at 6:50 p.m.

The NRC sent an Augmented Inspection Team (AIT) on February 18, 2000, to review the causes, safety implications, and licensee actions associated with the event. The AIT developed a sequence of events, determined the risk significance of the event, and assessed the response by the plant staff and management. The cause of the tube failure was outside the scope of this inspection and is currently being reviewed separately by the NRC. The AIT's report is presented in Inspection Report 05000247/2000-02, dated April 28, 2000 (Accession Number ML003710036).
Discussion
The event was risk significant. It involved a steam generator tube failure that resulted in an initial primary-to-secondary leak of reactor coolant of approximately 146 gallons per minute and required an "Alert" declaration (the second level of emergency action in the NRC-required emergency response plan). The event resulted in a minor radiological release to the environment that was well within regulatory limits. No radioactivity was measured offsite above normal background levels, and the event did not adversely impact the public health and safety.

The licensee performed the necessary actions to protect the health and safety of the public. Specifically, the operators promptly and appropriately took those actions in the emergency operating procedures to trip the reactor, isolate the affected steam generator, and depressurize the reactor coolant system. Additionally, the necessary event mitigation systems worked properly. Notwithstanding the above actions, the AIT identified performance problems in several broad areas that challenged operators, complicated the event response, delayed achieving the cold shutdown condition, and affected the radiological release. The problems involved operator performance, procedure quality, equipment performance, technical support, and emergency response.
Operator Performance
Some operator performance problems were noted during the plant cooldown phase involving the following:
- While attempting to cool down the reactor coolant system (RCS), the   reactor operator initiated an excessive cooldown rate that exceeded procedural   and Technical Specification limits. The excessive cooldown led to several   conditions that complicated the subsequent event response and delayed the RCS   cooldown.  
- Operators were slow to recognize configuration lineup problems that (1)   prevented successful operation of the auxiliary spray system to lower RCS   pressure and (2) delayed heatup of the RHR system. 
Procedure Quality
The procedures adequately guided the initial operator response; however, several procedure problems were identified that delayed the cooldown and depressurizing of the RCS. Procedure deficiencies affected Standard Operating Procedures, Emergency Operating Procedures, and Emergency Plan Implementing Procedures. Specific activities included initiation of RHR cooling, initiation of component cooling water alignment, use of auxiliary pressurizer spray, use of methods to monitor RCS temperature to maintain cold shutdown conditions, and initiation of emergency response organization (ERO) notifications. Station personnel were previously aware of the procedure issue involving initiation of RHR cooling but had not corrected the problem before this event.
Equipment Performance
The necessary event mitigation systems, including the reactor protection system, the auxiliary feedwater system, and the safety injection system, functioned properly. However, several longstanding equipment performance problems were identified that challenged operators during this event:
- Two losses of condenser vacuum resulted from problems with the operation   of the automatic steam supply pressure control valve to the steam jet air   ejectors, and the #22 condenser vacuum pump.  
- The isolation valve seal water system became inoperable during the event   and required operator action and an entry into a Technical Specification   Limiting Condition for Operation Action Statement.  
- A containment entry was required to install a temporary nitrogen supply to   the pressurizer power-operated relief valve to compensate for a design   deficiency. This action was required before placing the overpressure   protection system in service.  
- The steam generator leak rate monitoring equipment had been degraded for   an extended period, and limited the amount of steam generator leak rate   information available to the operators before the event. 

The AIT determined that the number and duration of the equipment problems reflected weaknesses in engineering, corrective action processes, and operational support at the station. The licensee's response to a number of the equipment problems identified during the event reflected an acceptance of "working around" the problem rather than fixing it.
Emergency Response
The ERO took the necessary steps to ensure the protection of public health and safety. The operators properly classified the event, and the licensee implemented a thorough peer review of the emergency response to this event. The AIT identified several emergency plan and implementing procedure problems similar to those identified by the licensee's peer review team, including the following:
- The emergency response staff was slow to activate the emergency   facilities.  
-  The licensee was slow to establish accountability (i.e., identify the   location) of emergency response personnel. 
- The emergency response data system (ERDS) was inoperable for the first   several hours of the event as a result of a pre-existing equipment   problem.  
- Problems were noted in the implementation of the media response   plan.  
- Problems were identified involving the timeliness and quality of technical   support provided to the operators. 

The licensee developed and was in the process of implementing an emergency response improvement plan before the event.

This information notice requires no specific action or written response. However, recipients are reminded that they are required to consider industry-wide operating experience (including NRC information notices) when practical when setting goals and performing periodic evaluations under Section 50.65, "Requirements for monitoring the effectiveness of maintenance at nuclear power plants," of Part 50 of Title 10 of the Code of Federal Regulations. If you have any questions about the information in this notice, please contact the one of the technical contacts listed below or the appropriate Office of Nuclear Reactor Regulation (NRR) project manager.
/RA by John Tappert Acting For/       
Ledyard B. Marsh, ChiefEvents Assessment, Generic Communications       and Non-Power Reactors BranchDivision of Regulatory Improvement       ProgramsOffice of Nuclear Reactor Regulation
Technical contacts:Eric Benner, NRR301-415-1171E-mail: ejb1@nrc.govLawrence Doerflein, Region I610-337-5378E-mail:       ltd@nrc.govPeter Eselgroth, Region I610-337-5234E-mail: pwe@nrc.govRaymond Lorson, Region I603-474-3589E-mail:   rkl@nrc.govAttachment:List of Recently Issued NRC Information Notices(ADAMS Accession Number ML003726124)