FINAL AIR POLLUTION CONTROL CONSTRUC TION PERMIT

EI FACILITY NO: 230006260 CONSTRUCTION PERMIT NO.: 11

- RSG

- 182

TYPE:
Construction Permit for Process es: P34, P35, P36

In compliance with the provisions of Chapter 285, Wis. Stats., and Chapters NR 400 to NR 499, Wis. Adm. Code,

Name of Source: Wisconsin Electric Power Company, D/B/A We Energies

Street Address: 8000 95th St reet
, Pleasant Prairie, Kenosha County, Wisconsin

Responsible Official, & Title: Tom Ventimiglia, Asset Manager

- P4

is authoriz ed to replace the existing dust collection systems of the in

- plant coal transfer system and the coal crusher
house described in the plans and specifications dated October 12, 2011 (application received)

, and to initially operate the in

- plant coal transfer system and the coal crusher house with new dust collection systems in conformity
with the conditions herein . The authority to construct, modify, replace and/or reconstruct any process covered in this Construction Permit expires eighteen (18) months from t he date of issuance. This approved period to construct, modify, replace and/or reconstruct may be extended for up to 18 months upon request for cause, prior to expiration, unless otherwise specified by this construction permit. The conditions of this const ruction permit are permanent and may only be revised through a revision of the construction permit or through the issuance of a new construction permit. [s. 285.60(1), Wis. Stats.]

Conditions of the construction permit marked with an asterisk (*) have been created outside of the Wisconsin’s federally approved State Implementation Plan (SIP) and are not federally enforceable.

This authorization requires compliance by the permit holder with the emission limitations, monitoring requirements
and other terms and conditions set forth in Parts I and II hereof.

Dated at Sturtevant , Wisconsin October 29, 2012

STATE OF WISCONSIN DEPARTMENT OF NATURAL RESOURCES For the Secretary

By /s/ Daniel Schramm Daniel Schramm Air Management Supervisor Milwaukee Service Cen terFID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 2 of 16

Part I

A. Process P34 , Control Device C34 (baghouse), Stack S34

– In

- Plant Coal Transfer System Unit 1

. Process P35, Control Device C35 (baghouse), Stack S35

– In

- Plant Coal Transfer System Unit 2.

Pollutant a. Limitations b. Compliance Demon stration c. Reference Test Methods, Recordkeeping and Monitoring Requirements

1. Particulate Matter

Emissions

Note: Also see I.A .3 for requirements under NSPS for Coal Preparation and Processing Plants. (1) Particulate matter (total PM) emissions from each stack (Stacks S34 and S35 ) may not exceed 1.71 pounds per hour. [s s . 285.65 (3), (7), Wis. Stats.]
(2 ) Particulate matter (total PM) emissions from each stack (S tack s S34 and S35) may not exceed :

E = 17.31 P 0.16

Where, E = allowable emissions in poun ds per hour P = process weight rate in tons per hour [ s. NR 415.05(2), Wis. Adm. Code] (1) The permittee shall operate a baghouse system (C34 and C35 ) to control particulate matter emissions from P34 and P35

. [s. 285.65(3), Wis. Stats.]
(2 ) Each baghouse shall be equipped with instrumentation to monitor the pressure drop across the baghouse and an alarm system

. [s. NR 439.055(1), Wis. Adm. Code]
(3) The permittee shall monitor the differential pressure across each baghouse (C34 and C35 ). The differentia l pressure monitoring and alarm system shall be in operation at all times the baghouse system is in operation. If the differential pressure falls below 0.1 inches of water column or a minimum pressure drop approved by the Department, in writing, an alarm shall signal an operator and an inspection of the hopper and bag c ollectors shall be performed and

any necessary remedial action shall be taken.
[s. 285.65(3), Wis. Stats.]
(4) The permittee shall p erform an initial performance test on stacks S34 and S35 t o demonstrate compliance with the particulate matter emission limit in condition I.A.1.a.(1) within 180 days of the date P34 and P35 commences operation after the change (i.e. first time any process related air contaminant is emitted into the ambient air v ia stack s S34 and S35 ) , while In

- Plant Coal Transfer (1) Reference Test Method for Particulate Matter Emissions : Whenever compliance emission testing is required to demonstrate compliance with condition I.A.1.a.(1) , U.S. EPA Method 5 or 17 in 40 CFR Part 60, Appendix A including condensable back half emissions (Method 202 in 40 CFR Part 51, Appendix M) or any other method approved by the Department in writing shall be used to demonstrate co mpliance.
[s. NR 439.06(1), Wis. Adm. Code]
(2) The permittee shall inspect the baghouse s (C34 and C35 ) daily. [s. 285.65(3), Wis. Stats. , s. NR 439.055(1), Wis. Adm. Code ]
(3) The permittee shall keep records of:
(a) The date and time of baghouse differen tial pressure alarms;
(b) Any corrective actions taken as a result of the inspection of the baghouse s or alarms.
[s. NR 439.04(1)(d), Wis. Adm. Code]FID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 3 of 16

A. Process P34 , Control Device C34 (baghouse), Stack S34

– In

- Plant Coal Transfer System Unit 1

. Process P35, Control Device C35 (baghouse), Stack S35

– In

- Plant Coal Transfer System Unit 2.

Pollutant a. Limitations b. Compliance Demon stration c. Reference Test Methods, Recordkeeping and Monitoring Requirements System is operating at capacity or as close to capacity as practicable or at a capacity approved by the Department in writing

. [s. 285.65(3), Wis. Stats., s. NR 439. 075(1), Wis. Adm. Code ]

Note: The a bove required test for total PM (filterable and condensable) may be conducted in conju n ction with the initial performance test for particulate matter (filterable o nly) required in condition I.A.3.b.(1)

. (5) The tests required in condition I.A.1.b.(4) shall be performed for each of the following two scenarios:
(a) Coal on belt
(b) Coal not on belt
[s. 285.65(3), Wis. Stats.]

2. Visible Emissions

Note: Also see I.A .3 for requirements under NSPS for Coal Preparation and Proce ssing Plants. (1 ) Number 1 on the Ringlemann chart or 20% opacity.
[s. NR 431.05, Wis. Adm. Code] (1) The permittee shall comply with requirements in I.A.1.b. (1) through (3)

. [s . 285.65(3), Wis. Stats. ] (1) Reference Test method s for Visible Emissions : Whenever compliance emission testing is required to demonstrate compliance with conditi on I.A.2.a.(1 ), U.S. EPA Method 9 in 40 CFR Part 60, Appendix A, shall be used to demonstrate compliance. [s. NR 439.06(9)(a)1., Wis. Adm. Code]

3. New Source Performa nce Standards (NSPS) for Coal Preparation and Processing
Plants

(40 CFR Part 60, Subpart Y) (1) On and after the date on which the performance test is conducted or required to be completed under 40 CFR 60.8, whichever date comes first, the permittee must m eet the requirements in (a) and (b) below.
(a) The permittee must not cause to be discharged into the atmosphere any gases which exhibit 10 percent (1) The permittee must conduct performance tests according to the requirements of s. NR 440.08, Wis. Adm. Code (40 CFR 60.8) to demonstrate compliance with the emission standards in condition I. A.3 .a.(1)(a) and (b)
as sp ecified in conditions I.A.3 .b.(2) and (3) below.
[ss. 285.65(3) and (13), Wis. Stats., 40 CFR 60.255(b)(1), s. NR 440.08, Wis. Adm. (1) Reference Test M ethod for Visible Emissions : The permittee must determine compliance with the opa city standard in condition I.A.3 .a.(1)(a) as specified in paragraphs (a) through (b) below.
(a) Method 9 of Appendix A

- 4 (of 40 CFR P art 60) and the procedures in 40 CFR 60.11 must be used to determine opacity, with the exceptions specified in (i) and (ii)FID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 4 of 16

A. Process P34 , Control Device C34 (baghouse), Stack S34

– In

- Plant Coal Transfer System Unit 1

. Process P35, Control Device C35 (baghouse), Stack S35

– In

- Plant Coal Transfer System Unit 2.

Pollutant a. Limitations b. Compliance Demon stration c. Reference Test Methods, Recordkeeping and Monitoring Requirements opacity or greater.
(b) The permittee must not cause to be discharged into the atmosphere from any mechanica l vent on an affected facility gases which contain particulate matter in excess of 0.010 gr/dscf (0.023 g/dscm).
[s. 285.65(13), Wis. Stats., 40 CFR 60.254(b), 40 CFR 60.250(d)] Code]
(2) For each Process P34, P35:
The permittee shall perform an initial performance test for the particulate matter standard. Thereafter, a new performance test must be conducted according to the requirements in (a) through (c) below, as applicable.
(a) If the results of the most recent performance test demonstrate that em issions are greater than 50 percent of the emission standard, a new performance test must be conducted within 12 calendar months of the date that the previous perfor mance test was required to be completed.
(b) If the results of the most recent performance test demonstrate that emissions are 50 percent or less of the emission standard, a new performance test must be conducted within 24 calendar months of the date that the previous performance test was required to be completed.
(c) If affected facilities have not operated for the 60 calendar days prior to the due date of a performance test, the permittee is not required to perform the subsequent performance test until 30 calendar days after the next operating day.
[s. 285.65(13), Wis. Stats., 40 CFR 60.255(b)(1)]
(3) For each Process P34, P35:
The permittee shall perform an initial belo w: (i) The duration of the Method 9 of Appendix A

- 4 (of 40 CFR P art 60) performance test shall be 1 hour (ten 6

- minute averages).
(ii) If, during the initial 30 minutes of the observation of a Method 9 of Appendix A

- 4 (of 40 CFR P art 60) performance test, all of the 6

- minute average opacity readings are less than or equal to half the applicable opacity limit, then the observation period may be reduced from 1 hour to 30 minutes.
(b) A visible emissions observer may conduct visible emission observation s for up to three fugitive, stack or vent emission points within a 15

- second interval if the following conditions in (i) through (iii) below are met:
(i) No more than three emissions points may be read concurrently.
(ii) All three emissions points must be within a 70 degree viewing sector or angle in front of the observer such that the proper sun position can be maintained for all three points.
(iii) If an opacity reading for any one of the three emissions points is within 5% opacity of the appl icable opacity standard, then the observer must stop taking readings for the other two points and continue reading just that singleFID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 5 of 16

A. Process P34 , Control Device C34 (baghouse), Stack S34

– In

- Plant Coal Transfer System Unit 1

. Process P35, Control Device C35 (baghouse), Stack S35

– In

- Plant Coal Transfer System Unit 2.

Pollutant a. Limitations b. Compliance Demon stration c. Reference Test Methods, Recordkeeping and Monitoring Requirements performance test for the opacity standard. Thereafter, a new performance test must be

con ducted according to the requirements in (a) through (b) below, as applicable, except as provided for in c ondition I.A.3 .b.(4).
(a) If any 6

- minute average opacity reading in the most recent performance test exceeds half the opacity limit, a new performance test must be conducted within 90 operating days of the date that the previous performance test was required to be completed.
(b) If all 6

- minute average opacity readings in the most recent performance test are equal to or less than half the opacity limit, a new performance test must be conducted within 12 calendar months of the date that the previous performance test was required to be completed.
[s. 285.65(13), Wis. Stats., 40 CFR 60.255(b)(2)]
(4) As an alternative to meeting the
requ irements in conditio n I.A.3 .b.(3), the permittee may elect to comply with the requirements in 40 CFR 60.255(f)(1) or (2).
[s. 285.65(13), Wis. Stats., 40 CFR 60.255(f)] point.
[s. 285.65(13), Wis. Stats., 40 CFR 60.257(a)]
(2) Reference Test M ethod for Particulate Matter Emissions : The permit tee must determine compliance with the particulate ma tter standard in condition I.A.3 .a.(1)(b) using Method 5 or 17 in Appendix A of 40 CFR P art 60, incorporated by reference in s. NR 440.17, Wis. Adm. Code.
[ss. 285.65(3),(13), Wis. Stats., 40 CFR 60.257( b)(5), s. NR 440.42(5)(a), Wis. Adm. Code]
(3) Comply with condition s I.ZZZ.1. a.(1) through (3) for reporting and recordkeeping requirements under 40 CFR 60.258. [s. 285.65(13), Wis. Stats., 40 C FR 60.258, 40 CFR 60.250(d) ]FID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 6 of 16

B

. Process P36 , Control D evice(s) C36 (baghouse ) , Stack S36

– Coal Crusher House

. This process may use wet suppression as an alternative control.

Pollutant a. Limitations b. Compliance Demonstration c. Reference Test Methods, Recordkeeping and Monitoring Requirements

1

. Pa rticulate Matter
Emissions

Note: Also see I. B .3 for requirements under NSPS for Coal Preparation and Processing Plants. (1) Particulate matter (total PM) emissions from stack S36 may not exceed 1.15 pounds per hour

. [s s . 285.65 (3) and (7), Wis. Stats. , ss. NR 415.05(1) & (2), Wis. Adm. Code ] (1) The permittee shall use a baghouse (C36) or wet suppression system to control particulate matter emissions at all times the coal crusher house is in operation.
[s. 285.65(3), Wis. Stats.]
(2) The permittee sha ll monitor the differential p ressure across the baghouse (C36 ). The differential pressure monitoring and alarm system shall be in operation at all times the baghouse system is in operation. If the differential pressure falls below 0.1 inches of water col umn or a minimum pressure drop approved by the Department, in writing, an alarm shall signal an operator and an inspection of the hopper and bag collectors shall be performed and any necessary remedial action shall be taken. [s. 285.65(3), Wis. Stats.]
(3) Whenever the wet suppression system is in operation as the primary particulate matter emission control system for P36 , the permittee shall monitor and record the liquid flow rate once every 8 hours or once per day, whichever yields the greater number of

m easurements. [s. NR 439.055(2)(b)5., Wis. Adm. Code]
(4) The liquid flow rate to the wet suppression system during operation shall be as recommended by the manufacturer. [s. 285.65(3), Wis. Stats.]
(5 ) The permittee shall p erform an initial (1) Reference Test Method for Particulate Matter Emissions : Whenever compliance emission testi ng is required to demonstrate co mpliance with condition I. B .1.a.(1) , US EPA Method 5 or 17 in 40 CFR Part 60, Appendix A, including condensable back half emissions (Method 202 in 40 CFR Part 51, Appendix M ), or any other method approved in writing by the Department shall be used to demon strate compliance

. [s. NR 439.06(1), Wis. Adm. Code]
(2) The permittee shall inspect the baghouse (C36) daily. [s. 285.65(3), Wis. Stats., s. NR 439.055(1), Wis. Adm. Code]
(3) The permittee shall keep records of:
(a) The date and time of bag house differe ntial pressure alarms;
(b) Any corrective actions taken as a result of the inspections of the baghouse or alarms.
[s. NR 439.04(1)(d), Wis. Adm. Code]
(4) The permittee shall keep records of the liquid flow rate measurements required under condition I. B .1. b.(3).
[s. NR 439.04(1)(d), Wis. Adm. Code]FID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 7 of 16

B

. Process P36 , Control D evice(s) C36 (baghouse ) , Stack S36

– Coal Crusher House

. This process may use wet suppression as an alternative control.

Pollutant a. Limitations b. Compliance Demonstration c. Reference Test Methods, Recordkeeping and Monitoring Requirements performance te st for the particulate matter (total PM) emission limit in condition I. B .1.a.(1) for stack S36 within 180 days of the date P36 commences operation after the change (i.e. first time any process related air contaminant is emitted in to the ambient air via sta ck S36), while P36 is operating at capacity or as close to capacity as practicable

or at a capacity approved by the Department in writing.
[s. 285.65(3), Wis. Stats., s. NR 439.075(1), Wis. Adm. Code]

Note: The above required test for total PM (filterab le and condensable ) may be conducted in conju n ction with the initial performance test for particulate matter (filterable o nly) required in condition I. B .3 .b.(1). (6) The stack test shall be performed while the baghouse is used to control PM emissions from P36. The alternative wet suppression control system shall not be in operation during the stack test. [s. 285.65(3), Wis. Stats.]

2. Visible Emissions

Note: Also see I.B .3 for requirements under NSPS for Coal Preparation and Processing Plants. (1 ) Number 1 on the Ringlemann chart or 20% opacity.
[s. NR 431.05, Wis. Adm. Code] (1) Th e permittee shall comply with requirements in I. B .1.b.(1) through (3)

. [s. 285.65(3), Wis. Stats.] (1) Reference Test methods for Visible Emissions : Whenever compliance emission testing is required to demonstrate compliance with conditi on I. B .2.a.(1 ), U.S . EPA Method 9 in 40 CFR Part 60, Appendix A, shall be used to demonstrate compliance. [s. NR 439.06(9)(a)1., Wis. Adm. Code]

3 . New Source Performance Standards (NSPS) for Coal Preparation and Processing (1) On and aft er the date on which the performance test is conducted or required to be completed under 40 (1 ) The permittee must conduct performance tests according to the requirements of s. NR 440.08, Wis. Adm. Code ( 40 CFR 60.8 ) to (1) Reference Test method for Visible Emissions : The permittee must determine compliance with the opa city standard inFID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 8 of 16

B

. Process P36 , Control D evice(s) C36 (baghouse ) , Stack S36

– Coal Crusher House

. This process may use wet suppression as an alternative control.

Pollutant a. Limitations b. Compliance Demonstration c. Reference Test Methods, Recordkeeping and Monitoring Requirements

Plants

(40 CFR Part 60, Subpart Y) CFR 60.8, whichever date comes first, the permittee must meet the requirements in (a) and (b) below.
(a) The permittee must not cause to be discharged into the atmo sphere any gases which exhibit 10 percent opacity or greater.
(b) The permittee must not cause to be discharged into the atmosphere from any mechanical vent on an affected facility gases which contain particulate matter in excess of 0.010 gr/dscf (0.023 g/ dscm).
[s. 285.65(13), Wis. Stats., 40 CFR 60.254 (b), 40 CFR 60.250(d)] demonstrate compliance with the emission standards in co ndition I. B .3 .a.(1)(a) and (b)

as sp ecified in conditions I. B .3 .b.(2) and (3 ) below.

[s s . 285.65 (3) and (13), Wis. Stats., 40 CFR 60.255(b)(1) , s. NR 440.08, Wis. Adm. Code ]
(2 ) The permittee shall perform an initial performance test for the particulate mat ter standard. Thereafter, a new performance test must be conducted according to the requirements in (a) through (c) below, as applicable.
(a) If the results of the most recent performance test demonstrate that emissions from the coal crusher house (S tack S 36) are greater than 50 percent of the emission standard, a new performance test must be conducted within 12 calendar months of the date that the previous performance test was required to be completed.
(b) If the results of the most recent performance test demonstrate that emission s from the coal crusher house (S tack S36) are 50 percent or less of the emission standard, a new performance test must be conducted within 24 calendar months of the date that the previous performance test was required to be comple ted.
(c) If affected facilities at the coal crusher house have not operated for the 60 calendar days prior to the due date of a performance test, the permittee is not required to perform condition I. B .3 .a.(1)(a) as specified in
para graphs (a) through (b) below.
(a) Method 9 of Appendix A

- 4 (of 40 CFR part 60) and the procedures in 40 CFR 60.11 must be used to determine opacity, with the exceptions specified in (i) and (ii) below:
(i) T he duration of the Method 9 of A ppendix A

- 4 (o f 40 CFR part 60) performance test shall be 1 hour (ten 6

- minute averages).
(ii) If, during the initial 30 minutes of th e observation of a Method 9 of A ppendix A

- 4 (of 40 CFR part 60) performance test, all of the 6

- minute average opacity readings are le ss than or equal to half the applicable opacity limit, then the observation period may be reduced from 1 hour to 30 minutes.
(b) A visible emissions observer may conduct visible emission observations for up to three fugitive, stack or vent emission points within a 15

- second interval if the following conditions in (i) through (iii) below are met:
(i) No more than three emissions points may be read concurrently.
(ii) All three emissions points must be within a 70 degree viewing sector or angle in fro nt of the observer such that the proper sun position can beFID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 9 of 16

B

. Process P36 , Control D evice(s) C36 (baghouse ) , Stack S36

– Coal Crusher House

. This process may use wet suppression as an alternative control.

Pollutant a. Limitations b. Compliance Demonstration c. Reference Test Methods, Recordkeeping and Monitoring Requirements the subsequent performance test until 30 calendar days after the ne xt operating day.
[s. 285.65(13), Wis. Stats., 40 CFR 60.255(b)(1)]
(3 ) The permittee shall perform an initial performance test for the opacity standard. Thereafter, a new performance test must be conducted according to the requirements in (a) through (b) below, as applicable , except as provided for in c ondition I. B .3 .b.(4 )

. (a) If any 6

- minute average opacity reading in the most recent performance test exceeds half the opacity limit, a new performance test must be conducted within 90 operating days of the date that the previous performance test was required to be completed.
(b) If all 6

- minute average opacity readings in the most recent performance test are equal to or less than half the opacity limit, a new performance test must be conducted within 12 cale ndar months of the date that the previous performance test was required to be completed.
[s. 285.65(13), Wis. Stats., 40 CFR 60.255(b)(2)]
(4 ) As an alternative to meeting the

requ irements in condition I. B .3 .b.(3 ), the permittee may elect to comply with th e requirements in 40 CFR 60.255(f)(1) or (2).
[s. 285.65(13), Wis. Stats., 40 CFR 60.255(f)] maintained for all three points.
(iii) If an opacity reading for any one of the three emissions points is within 5% opacity of the applicable opacity standard, then the observer must stop taki ng readings for the other two points and continue reading just that single point.
[s. 285.65(13), Wis. Stats., 40 CFR 60.257(a)]
(2) Reference Test method for Particulate Matter Emissions : The permittee must determine compliance with the particulate ma tter standard in condition I. B .3 .a.(1)(b) using Method 5 or 17 in Appendix A of 40 CFR part 60, incorporated by reference in s. NR 440.17, Wis. Adm. Code.

[s s . 285.65( 3) ,(13) , Wis. Stats., 40 CFR 60.257(b)(5), s. NR 440.42(5)(a), Wis. Adm. Code ]
(3) Comply wit h condition s I.ZZZ.1. a.(1) through (3) for reporting and recordkeeping requirements under 40 CFR 60.258. [s. 285.65(13), Wis. Stats., 40 C FR 60.258, 40 CFR 60.250(d) ]FID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 10 of 16

C. Process P34 , Control Device(s) C34 (baghouse), Stack S34

– Coal Crusher House.

Process P35 , Control Device(s) C35 (baghouse), Stack S35

– Coal Crusher House.

Process P36 , Control Device(s) C36 (baghouse), Stack S36

– Coal Crusher House. Note: P36 may use wet suppression as an alternative control. Condition Type a. Condition s 1. Source Obligation (1) The permittee shall monitor the emissions of any regulated NSR air contaminant that could increase as a result of the project
covered under t he construction permit 11

- RSG

- 182 and that is emit ted by any emissions unit in P34, P3 5, and P36 and calculate and maintain a record of the annual emissions, in tons per year on a calendar year basis, for a period of 10 years following resumption of regular operations after the change.

[s. NR 405.16(3)(d), W is. Adm. Code ]

(2) The permittee shall submit a report to the Department if the annual emissions, in tons per year, from the project covered
under the construction permit 11

- RSG

- 182 , exceed the baseline actual emissions by a significant amount for that regulated NSR air contaminant, and if the emissions differ from the preconstruction proje ction that was provided to the D epartment. The report shall be submitted to the Department within 60 days after the end of the year. The report shall contain all of the following:

(a) The name, address and telephone number of the major stationary source.

(b) The annual emissions as calculated.

(c) Any other information that the owner or operator wishes to include in the report, e.g., an explanation as to why the emission s differ from the preconstruction projection.

[s. NR 405.16(3)(f), W is. Adm. Code ]

(3 ) The permittee shall make the information required to be documented and maintained pursuant to I.C.1.a. (1) available for inspection, upon request by the D epartment or the general public.

[s. NR 405.16( 4) , Wis. Adm. Co de ]FID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 11 of 16

ZZZ. Conditions Applicable to the Entire Facility.

Note: This section of permit 11

- RSG

- 182 does not include all the requirements applicable to the facility. Condition Type a. Condi tions, Compliance Demonstration

1. Rep orting and
recordkee ping requirements
under 40 CFR Part 60, S ubpart
Y

– for P34, P35 , and P36

(40 CFR 60.258) (1) The owner or operator of a coal preparation and processing plant that commenced construction, reconstruction, or modification after April 28, 2008, shall maintain in a logbook (written or electronic) on

- site and make it available upon request. The logbook shall record the following:

(a) The manufacturer’s recommended maintenance procedures and the date and time of any maintenance and inspection activities and the results of those activities. Any variance from manufacturer recommendation, if any, shall be noted.

(b) The date and time of periodic coal preparation and processing plant (P34, P35, P36) visual observations, noting those sources with visible emissions along with corrective actions taken to reduce visible emissions. Results from the actions shall be noted.

(c) The amount and type of coal processed each calendar month.

(d) The amount of chemical stabilizer or water purchased for use in the coal preparation and processing plant (P34, P35, P36)

.

(e) Monthly certification that the dust suppressant systems were operational when any coal was processed and that manufacture r’s recommendations were followed for all control systems. Any varianc e from the manufacturer’s recommendations, if any, shall be
noted.

(f) Monthly certification that the fugitive coal dust emissions control plan was implemented as described. Any variance fro m the plan, if any, shall be noted. A copy of the applicable fug itive coal dust emissions control plan and any letters from the Administrator providing approval of any alternative control measures shall be maintained with the logbook. Any actions, e.g. objections, t o the plan and any actions relative to the alternativ e control measures, e.g. approvals, shall be noted in the logbook as well.

(g) During a performance test of control equipment other than a wet scrubber, and each operating day thereafter, the owner or operator shall record the measurements of the reagent i njection flow rate, as applicable.

[s. 285.65(13), Wis. Stats., 40 CFR 60.258(a)(1)

- (6),(10)]

(2) The permittee shall submit the results of initial performance tests to the Administrator or to the Department , consistent with the provisions of 40 CFR 60.8. The owner or operator who elects to comply with the reduced performance testing provis ions of 40 CFR 60.255(c) shall include in the performance test report identification of each affected facility that will be subject to the reducedFID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 12 of 16

ZZZ. Conditions Applicable to the Entire Facility.

Note: This section of permit 11

- RSG

- 182 does not include all the requirements applicable to the facility. Condition Type a. Condi tions, Compliance Demonstration testing.

[s. 285.65 (13), Wis. Stats., 40 CFR 60.258(c)]

(3) W ithin 60 days after the date of completing each performance evaluation conducted to demonstrate compliance with this subpart (40 CFR part 60, subpart Y), the permittee must submit the test data to EPA by successful ly entering the data electronically into EPA’s
WebFIRE data base available at http://cfpub.epa.gov/oarweb/index.cfm?action=fire.main . For performance tests that cannot be
entered into WebFIRE (i.e., Method 9 of appendix A

- 4 of 40 CFR part 60 opacity performance tests) the permittee must mail a summary copy to United States Environmental Protection Agency; Energy Strategies Group; 109 TW Alexander DR; mail code:
D243

- 01; RTP, NC 27711.

[ s. 285.65(13), Wis. Stats., 40 CFR 60.258(d)]FID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 13 of 16

ZZZ. Conditions Applicable to the Entire Facility.

Note: This section of permit 11

- RSG

- 182 does not include all the requirements applicable to the facility. Condition Type a. Condi tions b. Compliance De monstration
, Recordkeeping and Monitoring Requirements

2

. Construction Permit

11

- RSG

- 182

Transitional Language (1 ) Notifications. The permittee shall inform the Department of the following dates:

(a) The date cons truction commences on
modified emission un it(s ) addressed in this permit

.

(b) The date the modified emission unit(s) becomes operational.

Note: For purposes of this permit, “operational” shall be defined as the first time of any process related air
contaminant is emitted into the ambient
air after modification

.

[s. NR 439.03(1), Wis . Adm. Code ]

(2) Construction Authorization Expiration. The Authorization to Construct, under Construction Permit 11

- RSG

- 182 expires 18 months after the
date of issuance. Construction or modification and an initial opera tion period for equipment shakedown, testing and Department evaluation of operation to assure conformity with the permit
conditions is authorized for each emissions unit covered in this permit. Please note that the sources covered by this permit are requir ed to meet all (1) Notifications . The permittee shall submit to the Department of Natural Resources, Southeast R egion Air Program, Sturtevant Service Center in writing, within 15 days of the date the event, the following:
(a) (a) The date construction commences on dust control systems (C34, C35, C36) addressed in Permit 11

- RSG

- 182.
( (b) The date the new dust col lection systems (C34, C35, C36) become operational.
[s. NR 439.04(1)(d), Wi s. Adm. Code ]

(2 ) Emission Stack Testing. Upon completion of any required compliance emission
tests of the emission units P34, P35 and P36 , the permittee shall submit to the Departm ent of Natural Resources, Southeast Region Air Program, Sturtevant Service
Center two copies of the report on the tests for evaluation within 60 days of the date the tests were completed.

[s. NR 440.13(3)(b ), Wi s. Adm. Code , s. NR 439.07(9), Wis. Adm. Code , ss. 285.65(3),(13), Wis. Stats. ]

(3 ) Submittal of Compliance Testing Information and other updates. The permittee shall submit to the department any updates of the permit application. Updates are required if any changes that occur which are not specified or described in the plans and specifications dated October 12 , 2011 (application received) . The updates shall be made within 60 days of the date of the change. Other information to be submitted shall include the notification requirements and stack tests r esults. The continued

op eration of the modified emission units addressed in this construction permit are prohibited once the authorization to construct expires per Condition ZZZ.2 .a.(2), unless any required updates have been submitted and the permittee has satisfied the notification requirements of Co ndition ZZZ.2 .b.(1).

[s. NR 439. 04(1)(d), Wis. Adm. Code ]

( 4 ) Submittal of Malfunction Prevention and Abatement Plan. The permittee shallFID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 14 of 16

ZZZ. Conditions Applicable to the Entire Facility.

Note: This section of permit 11

- RSG

- 182 does not include all the requirements applicable to the facility. Condition Type a. Condi tions b. Compliance De monstration
, Recordkeeping and Monitoring Requirements

emission limits and conditions contained in the permit at all times, including during the initial operation period. If 18 months is an insufficient time period for construction or modification, equipment shakedown, testing and Department

eva luation of operation, the permit holder may request and the Department may approve in writing an extension of this permit. The conditions of the construction permit are permanent, unless revised, superseded or revoked.

[ss. 285.60(1)(a)2. and 285.66(1), Wi s. Stats., and s. NR 406.12, Wis. Ad m. Code ]

(3 ) Malfunction Prevention and
Abatement Plan. The permittee shall update the facility’s Malfunction Prevention and Abatement Plan to include the operation and maintenance of the control equipment
associated wi th the emission units P34, P35 and P36 no later than 60 days after the date each unit becomes operational after
modification

.

[s. NR 439.11, Wis. Adm. Code ]

(a) (4) Stack Testing.

All (a) All t esting shall be performed while the submit a copy of the facility’s updated Malfunction Prevention and Aba tement Plan

to the Department within 60 days of being updated.

[ss. NR 439.04(1)(d) and NR 439.11(1)(h), Wis. Adm. Code ]

( 5 ) All submittals described in this permit shall be made in writing and include the name of the facility, the construction permit nu mber and a description of the affected emission unit(s).

[s. NR 439.0 4(1)(d), Wis. Adm. Code ]FID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 15 of 16

ZZZ. Conditions Applicable to the Entire Facility.

Note: This section of permit 11

- RSG

- 182 does not include all the requirements applicable to the facility. Condition Type a. Condi tions b. Compliance De monstration
, Recordkeeping and Monitoring Requirements emission unit is operating at capacity or as close to capacity as practicable.

[s. NR 439.07(1), Wis. Adm. Code , s. 285.65(3), Wis. Stats. ]

(c) (b) For each process P34, P35 and P36 , t he Department shall be notified at lea st 20 working (business) days prior to stack testing, so a Dep artment representative can witness the testing. At the time of notification, a compliance emission test plan shall also be submitted to the Department for approval. When approved in writing, an equivalent test method may be substituted for
the reference te st method. The notification and test plan shall be submitted to the Wisconsin Department of Natural Resources,
Southeast R egion Air Program, Sturtevant
Service Center.

[s. NR 439.07(2), Wis. Adm. Code]

(b) (c) For each process P34, P35 and P36, t he Departm ent shall be informed at lea st 30 working (business) days prior to stack testing (required by 40 CFR Part 60, S ubpart Y) , so a Department representative can witness the testing. If after 30 days notice for an initially scheduled performance test, there is a delay in conducting the scheduled performance test, the permittee shall notify theFID No. 230006260, Construction Pe rmit No. 11

- RSG

- 182 Page 16 of 16

ZZZ. Conditions Applicable to the Entire Facility.

Note: This section of permit 11

- RSG

- 182 does not include all the requirements applicable to the facility. Condition Type a. Condi tions b. Compliance De monstration
, Recordkeeping and Monitoring Requirements Department as soon as possible of any delay in the original test date, either by providing at least 7 days prior notice of the rescheduled date of the performance test, or by arranging a rescheduled date with the Department by mutual agreement. At the time of notification, a compliance emission test plan shall also be submitted to the Department for approval. The notification and test plan shall
be submitted to the Wisconsi n Department of Natural Resources, Southeast Region Air Program, Sturtevant Service Center.

[s. NR 440.08(4 ), Wis. Adm. Code , s. 285.65(3), Wis. Stats. ]

205598

- 2