Index | Site       Map | FAQ | Facility       Info | Reading       Rm | New | Help | Glossary | Contact UsProtecting People and the EnvironmentUNITED STATES NUCLEAR REGULATORY COMMISSION -   About NRC    - The     Commission 
  - Statutory Authority 
  - Strategic Plan 
  - Budget &      Performance 
  - Organization & Functions 
  - Locations 
  - History 
  - Values 
  - Policymaking 
  - Radiation Protection 
  - Fire Protection 
  - How We Regulate 
  - Grants 
  - Civil Rights 
  - 
- NuclearReactors    - Operating Reactor Locations 
  - Reactor Quick Links 
  - Power Reactors 
  - Research and Test     Reactors 
  - Operating Reactors 
  - Operator Licensing 
  - New Reactors 
  - Operator     Licensing for New Reactors 
  - Reactor Safety Research 
  - Advisory Comm (ACRS) 
  - Decommissioning     of Nuclear Facilities 
  - 
- NuclearMaterials    - Fuel Cycle Facility Locations 
  - Uranium     Recovery Locations 
  - Materials Quick Links 
  - Special Nuclear Material 
  - Source Material 
  - Byproduct Material 
  - Med, Academic & Ind Uses 
  - Source Materials Facilities 
  - Uranium Recovery 
  - Fuel Cycle Facilities 
  - Materials     Transportation 
  - Materials Research 
  - Advisory Comm (ACMUI) 
  - Decommissioning     of Nuclear Facilities 
  - Materials     Environmental Reviews 
  - 
- RadioactiveWaste    - Waste Quick Links 
  - Low-Level Waste 
  - Waste Incidental to     Reprocessing 
  - Incidental Waste Criteria 
  - High-Level Waste 
  - Uranium Mill Tailings 
  - LLW Disposal 
  - HLW Disposal 
  - Spent Fuel Storage 
  - Spent Fuel Transport 
  - Waste Research 
  - 
- NuclearSecurity    - Security     Spotlight 
  - NRC     Responsibilities 
  - Domestic Safeguards 
  - Radioactive Material Security 
  - Facility Protection 
  - Nuclear Material Control 
  - International Safeguards 
  - Information Security 
  - Emergency     Preparedness 
  - &; 
- Public Meetings&   Involvement    - Public Meeting Schedule 
  - Commission     Schedule 
  - Conferences & Symposia 
  - Documents for Comment 
  - Brochures & Fact Sheets 
  - Involving Stakeholders 
  - Info Quality Guidelines 
  - Rulemaking Process 
  - Licensing 
  - Enforcement 
  - Hearing Process 
  - Hearing Applications 
  - 

Home       > Electronic Reading       Room       > Document       Collections       > General       Communications       > Information       Notices       > 1999       > IN 99-14

UNITED STATESNUCLEAR REGULATORY COMMISSIONOFFICE OF NUCLEAR REACTOR REGULATIONWASHINGTON, D.C. 20555-0001

May 5, 1999
NRC INFORMATION NOTICE 99-14:UNANTICIPATED REACTOR WATER DRAINDOWN AT QUAD CITIES UNIT 2, ARKANSAS       NUCLEAR ONE UNIT 2, AND FITZPATRICK - Addressees 
- Purpose 
- Description   of Circumstances    - Quad     Cities Unit 2 
  - Arkansas     Nuclear One Unit 2 
  - FitzPatrick 
- Discussion 
Addressees
All holders of licenses for nuclear power, test, and research reactors.
Purpose
The U.S. Nuclear Regulatory Commission (NRC) is issuing this information notice to alert addressees to the potential for personnel errors during infrequently performed evolutions that result in, or contribute to, events such as the inadvertent draining of water from the reactor vessel during shutdown operations. It is expected that recipients will review the information for applicability to their facilities and consider actions, as appropriate, to prevent a similar occurrence. However, suggestions contained in this information notice are not NRC requirements; therefore, no specific action or written response to this notice is required.
Description of CircumstancesQuad Cities Unit 2
On February 24, 1999, Quad Cities Unit 2 was in cold shutdown with reactor water temperature at 131 °F and reactor water level at 80 inches indicated level (normal level during operations is 30 inches indicated or 173 inches above the top of active fuel [TAF]). Core cooling was being maintained in a band of 120 °F to 170 °F by the "A" loop of the shutdown cooling mode of the residual heat removal (RHR) system after being switched from the "B" loop at 12:32 a.m. During the switch over the licensee inadvertently failed to close the "A" RHR minimum flow valve as required by the procedure. Sometime later operators noted a decreasing reactor water level and at about 1:02 a.m. secured the "2A" RHR pump and isolated shutdown cooling. At 1:55 a.m. operators restored the "2A" loop of shutdown cooling to the proper lineup and started the "2A" RHR pump. Water level had decreased to a minimum of about 45 inches indicated, and reactor water temperature had risen to a maximum of about 163 °F. Forced circulation of reactor vessel water using a reactor recirculation pump remained in effect throughout the event.

On the basis of post event reviews, it appears that the minimum flow valve in the "A" loop was left open because the nuclear station operator failed to ensure that the tasks were performed in the sequence specified in the operating procedures. The nuclear station operator who was directing the evolution from the control room gave the non-licensed operator permission to de-energize the breaker for the "A" RHR minimum flow valve operator before the valve was taken to the required closed position. De-energizing the breaker also removed power to the valve position indicator lights in the control room. Thus, when the nuclear station operator tried to verify that the valve was closed, there was no position indication in the control room to make that verification. The nuclear station operator made the incorrect assumption that the valve was already closed and moved to the next step in the procedure. This failure to close the "A" RHR minimum flow valve opened a drain path from the reactor to the suppression pool. To further complicate the event, the operating crew did not recognize that there was any problem until approximately 10 minutes had passed and the water level had decreased about 13 inches because of a misinterpretation of causes of the level decrease. After detecting the decrease, the operating crew was slow to react, which allowed the level to decrease another 20 inches before the operators isolated shutdown cooling which terminated the draindown. The licensee estimated that a total of 6000 to 7000 gallons was drained from the reactor to the suppression pool.

Operations staff practices including poor communications, poor activity briefings for high-risk activities, lack of effective pre-shift briefings, inadequate supervision of important control room activities, inadequate monitoring of control room panels, and slow event response may have contributed to the event. Although the unintended loss of inventory to the suppression pool highlighted significant weaknesses in plant operations, the safety significance was minimized by two features. First, a reactor recirculation pump remained in service throughout the event which served to distribute decay heat. Second, an automatic isolation of shutdown cooling would have occurred at 8 inches indicated level which would have stopped the draining event. An indicated water level of 8 inches corresponds to approximately 151 inches of water level above the TAF in the reactor core.
Arkansas Nuclear One Unit 2
On February 2, 1999, at Arkansas Nuclear One Unit 2, the operators were draining the refueling canal in preparation for installing the reactor vessel head. Refueling was complete and steam generator nozzle dams were installed. The operators were using the two low pressure safety injection (LPSI) pumps to drain the canal to the refueling water storage tank; one pump also served as the shutdown cooling pump. The rate of draindown was approximately 3.3 inches per minute. When the water level reached 105 inches, the reactor operator noted that level started to lower rapidly. Operators stopped one of the LPSI pumps and instructed a local operator to close the isolation valve to the refueling water tank. This manually operated valve required 55 turns of the handwheel to fully close. Within approximately 1.5 minutes, the reactor vessel level had dropped below the 65 inch level (where reduced inventory begins) and continued down to 56 inches before the valve could be fully closed. (Reference zero on these level instruments is the bottom of the hot leg, with mid-loop being defined at approximately 24 inches.) The average rate of level decrease between 105 inches and 56 inches was approximately 33 inches per minute. At its lowest level, 56 inches indicated, there were still 93 inches of water above the TAF. Using the high pressure safety injection (HPSI) pump the operators brought the level back up to 90 inches. The plant was in reduced inventory operations (below 65 inches) for approximately 7 minutes. During the event the level remained well above the point where LPSI pump cavitation would be expected. The licensee concluded that the safety significance of the event was minimal because multiple sources of makeup water were available, redundant mitigation equipment was available, and the operators were quick to recognize and respond to the event.

On the basis of post event reviews, it was determined that the procedure used for draining down the refueling canal was inadequate in that it incorrectly stated that the draindown should be secured at the 90-inch level. The procedure should have directed that the rate of draining be secured at the 106-inch level so that appropriate precautions could be taken before resuming the draindown. These precautions should have included reminders to the operating crew that below the 106-inch level the level will drop much more quickly due to the transition of pumping from a large volume in the refueling canal to a small volume in the reactor vessel. Therefore, in order to maintain control of the water level, the draindown rate should be decreased and an operator should be stationed to directly monitor the level.

Additional factors that contributed to this event include: the operators received little specific training on this evolution; the crew was inexperienced in performing this task; the task should have been classified as an infrequent task requiring a more thorough briefing; and, operators failed to station an operator in a position where he could directly monitor the water level in the refueling canal. Instead they monitored it remotely using a video camera that did not provide a clear picture of the water level.
FitzPatrick
On December 2, 1998, at the James A. FitzPatrick Nuclear Power Plant, the operators were in the process of reassembling the reactor following refueling. Operators were controlling the reactor vessel water level at 357 inches above TAF by adjusting the water discharge rate to compensate for the constant input from the control rod drive cooling water system. While in this condition, the licensees risk analysis requires that reactor vessel water level be monitored using two independent level indicators. To meet this requirement, the licensee designated a wide range indicator which provided indication up to the top of the reactor vessel and an RHR interlock level indicator which provided indication in the range from -150 inches to +200 inches as the instruments to be used during this evaluation.

In order for the wide-range level indicator to remain available with the reactor head removed, a temporary standpipe and fill funnel were used to replace a portion of the reference leg. At the time of the event, the licensee was in the process of removing this temporary standpipe and reinstalling the original reference leg components. As the water drained from the standpipe, it caused the wide-range level indicator to erroneously show an increasing water level. For a period of approximately one hour the operators in the control room, unaware that the ongoing maintenance would cause an error in the indicated water level, compensated for the apparent increasing level by increasing the discharge rate. This action had the effect of reducing the actual water level from 357 inches to 255 inches. During the same time period, the operators were also in the process of filling and venting the reactor feedwater piping, which could have affected the reactor water level. Once the normal reference leg piping had been reinstalled and the reference leg began to refill, the indicated level decreased from 357 inches to the actual level of 255 inches. The second level instrument, which does not come on-scale until the level goes below 200 inches, remained off-scale high.

When operators discovered the level discrepancy, they used a temporary pressure gauge connected to the reactor vessel low-point tap to confirm the actual water level. After confirming the accuracy of the wide-range indicator, they restored the reactor vessel water level to 357 inches. The 100-inch error represented approximately 14,000 gallons of water. The licensee determined that the safety significance of this event was low since the reactor was in cold shutdown with low decay heat and the reactor water level remained well above the TAF. In addition, the drain-down would have been limited by an automatic isolation of the draindown path, which would have occurred prior to vessel level reaching 177 inches above the TAF.

The licensee's post event review identified: weaknesses in the operator's knowledge of the reactor assembly process; lack of explicit detail in the reactor assembly procedure; and, weaknesses in the plant risk assessment process. Contrary to the assumption that two designated reactor water level indicators were available, only one indicator, the wide-range instrument, was available in the range above 200 inches. When the reference leg on the wide-range instrument was disassembled and drained, the one usable indicator was rendered unavailable. The second instrument was pegged off-scale high and remained that way throughout the event because the level never dropped below 200 inches. A post event review by the licensee indicated that other reactor water level instruments, remained operable during the event but, apparently the operators did not rely on these other instruments or notice the discrepancy between them and the wide range indicator. Proposed corrective actions included procedural enhancements to ensure that reactor level instrumentation credited by the outage risk assessment remains available during reactor disassembly and reassembly.
Discussion
Personnel errors appear to have caused, or contributed to, these three inadvertent reactor vessel draindown events. The likelihood of personnel errors is dependent upon the operator's knowledge of the task gained through previous experience and training. It is also dependent upon the quality of the procedures used to perform the task, the level of supervision, the adequacy of pre-job briefings, fatigue, and distractions resulting from multiple tasks. In each of the events, the plant staff made errors during a seldom-performed evolution. Because it was a seldom-performed evolution, more training, better pre-job briefings, closer supervision, and procedures that contain more details than those for frequently performed activities might have prevented these events.

This information notice requires no specific action or written response. If you have any questions about the information in this notice, please contact the technical contact listed below, the appropriate regional office, or the appropriate Office of Nuclear Reactor Regulation (NRR) project manager.
/s/'d byLedyard B. Marsh, ChiefEvents Assessment, Generic       Communications      And Non-Power Reactors       BranchDivision of Regulatory Improvement ProgramsOffice of Nuclear       Reactor RegulationTechnical contact:Chuck Petrone, NRR 301-415-1027 E-mail:   cdp@nrc.gov
REFERENCES:

NRC Integrated Inspection Report No. 50-333/98-08, issued February 10, 1999 (Accession No. 9902170348) for the James A. FitzPatrick Nuclear Power Plant for the period November 22, 1998, through January 10, 1999.
Attachment:List of Recently Issued NRC Information Notices(NUDOCS Accession Number 9905070080)