Skip to Main Page ContentSkip to SearchSkip to Site Map NavigationSkip to Footer Links

        - Home

        - FAQ
        - Glossary
        - Facility Locator
        - What's New
        - Site Help
        - Index A-Z
        - Contact Us
        - Browse Aloud
        - Email Updates

Report a Safety Concern

      - Nuclear Reactors  - Power Reactors
- Research & Test Reactors
- Operating Reactors
- Operator Licensing
- New Reactors
- Advanced Reactors
- Operator Licensing for New Reactors
- Nuclear Reactor Quick Links
 
      - Nuclear Materials  - Special Nuclear Material
- Source Material
- Byproduct Material
- Med, Ind, & Academic Uses
- Source Materials Facilities
- Uranium Recovery
- Fuel Cycle Facilities
- Materials Transportation
- Nuclear Materials Quick Links
 
      - Radioactive Waste  - Low-Level Waste
- Waste Incidental to Reprocessing
- High-Level Waste
- Uranium Mill Tailings
- Low-Level Waste Disposal
- High-Level Waste Disposal
- Storage of Spent Nuclear Fuel
- Transporation of Spent Nuclear Fuel
- Radioactive Waste Quick Links
 
      - Nuclear Security  - Domestic Safeguards
- Information Security
- Radioactive Material Security
- Contact Us
 
      - Public Meetings & Involvement  - The NRC Approach to Open Government
- About Meetings Open to the Public
- Conferences & Symposia
- Documents for Comment
- Facilitating Stakeholder Involvement
- NRC Information Quality Guidelines
- Subscribe to E-mail Updates
- Commission Schedule
- Public Meeting Schedule
 
      - NRC Library  - Basic References
- Document Collections
- ADAMS Public Documents
- Public Document Room
- Get Copies of Documents
- FOIA & Privacy Act Requests
- Photos & Video
- Records Management 
- Withholding of Sensitive Information
- FAQ Index
- Adjudications (Hearings)
 
      - About NRC  - The Commission
- Governing Legislation
- Plans, Budget, & Performance
- Organization & Functions
- Locations
- History
- Values
- Direction-Setting & Policymaking
- Radiation Protection
- Fire Protection
- How We Regulate
- Emergency Preparedness & Response
- Public Affairs
- Congressional Affairs
- International Programs
- State & Tribal Programs
- Alternative Dispute Resolution Programs
- Employment Opportunities
- Contracting Opportunities
- Grant Opportunities
- Civil Rights
 

Print

HomeNRC LibraryDocument CollectionsGeneral CommunicationsInformation Notices1993

# 

```



                                   UNITED STATES
                           NUCLEAR REGULATORY COMMISSION
                       OFFICE OF NUCLEAR REACTOR REGULATION
                              WASHINGTON, D.C.  20555

                                 February 18, 1993


NRC INFORMATION NOTICE 93-15:  FAILURE TO VERIFY THE CONTINUITY OF SHUNT TRIP  
                               ATTACHMENT CONTACTS IN MANUAL SAFETY INJECTION  
                               AND REACTOR TRIP SWITCHES 


Addressees

All holders of operating licenses or construction permits for nuclear power
reactors.

Purpose

The U.S. Nuclear Regulatory Commission (NRC) is issuing this information
notice to alert addressees to a surveillance test method that is not adequate
to verify the operability of the contacts in manually operated safety
injection and reactor trip switches.  It is expected that recipients will
review the information for applicability to their facilities and consider
actions, as appropriate, to avoid similar problems.  However, suggestions
contained in this information notice are not NRC requirements; therefore, no
specific action or written response is required.

Description of Circumstances

On May 19, 1992, the Houston Lighting and Power Company, the licensee for the
South Texas Project, issued a notification of an unusual event and began a
technical specification-required shutdown of both units.  The licensee had
discovered that it was not conducting adequate testing of the switch contacts
that directly actuate the shunt trip attachment of the reactor trip circuit
breakers.  These initiation contacts are actuated by either the manual safety
injection or reactor trip switches and are the means by which operator action
directly actuates the shunt trip, one of two means by which the breaker is
tripped, the other being the undervoltage trip.

The licensee had been performing surveillance tests of the safety injection
switches and the reactor trip switches without opening the associated block
switch (see attached simplified diagram of the manual reactor trip circuitry). 
If not opened, the block switch allows the same manual switch contacts that
actuate the undervoltage attachment to indirectly actuate the shunt trip
attachment.  Therefore, the manual switch contacts which directly actuate the
shunt trip attachment are not necessary for actuation of the shunt trip and,
therefore, not independently verified as operable.  This surveillance
inadequacy has also been identified at the Callaway Plant, the Seabrook
Nuclear Station, and the Wolf Creek Generating Station.  The above mentioned
licensees have since properly verified the operability of the manual switch
contacts.


9302120058.

                                                             IN 93-15
                                                             February 18, 1993
                                                             Page 2 of 3


Discussion

There are two manually operated safety injection switches and two manually
operated reactor trip switches.  Each switch contains circuitry which is
designed to initiate a reactor trip.  The attached diagram illustrates the
manner by which a reactor trip breaker is opened when any of the manual        
switches is engaged.  When a switch is operated, moveable contacts in that     
switch change state.  For example, when safety injection switch designated SI1
is engaged, the SI1 contacts in the 48 Vdc circuit open and SI1 contacts in    
the 125 Vdc circuit close.  The opened 48 Vdc SI1 contacts interrupt power to
the undervoltage trip coil (UV) of the undervoltage trip attachment. 
Concurrently, the closed SI1 contacts in the 125 Vdc circuit allow the shunt
trip coil (STC) of the shunt trip attachment to become energized.  

De-energizing the UV causes the armature of the undervoltage trip attachment
to make contact with and lift the trip lever of the associated reactor trip
breaker.  Energizing the STC causes the shunt trip attachment armature to also
make contact with and lift the trip bar of the associated reactor trip
breaker.  As a result of either of these actions, the circuit breaker opens to
initiate a reactor trip.

Opening of the SI1 contacts in the 48 Vdc circuit also de-energizes the auto   
shunt trip relay (STA) causing the associated STA contacts in the 125 Vdc
circuit to close.  The closed STA contacts provide an electrical path by which
the STC is energized, thus actuating the shunt trip attachment.  This path is
in parallel to the electrical path provided by the closed 125 Vdc SI1 contacts
when the switches are actuated.  

The licensee corrected their procedure as follows:  

     During continuity tests of the 125 Vdc SI1 contacts, the block switch
     that is shown in series with the STA contacts is held in the open
     position.  This action assures that the voltage measured at the terminal
     block of the reactor trip breaker results solely from the closure of the
     125 Vdc SI1 contacts and not from the closed STA contacts.  If the "block
     switch" is not held in the open position, it is not possible to
     independently verify the continuity of the 125 Vdc SI1 contacts. 
     Continuity checks of the 125 Vdc contacts in the other manually operated
     switches are made in the same way.  

Related Generic Communication

On May 23, 1985, the NRC issued Generic Letter 85-09 which described an
appropriate methodology for verifying the operability of moveable contacts in
the manual switches.
.

                                                             IN 93-15
                                                             February 18, 1993
                                                             Page 3 of 3


This information notice requires no specific action or written response.  If
you have any questions about the information in this notice, please contact
the technical contact listed below or the appropriate Office of Nuclear
Reactor Regulation (NRR) project manager. 


                                           ORIGINAL SIGNED BY


                                        Brian K. Grimes, Director
                                        Division of Operating Reactor Support
                                        Office of Nuclear Reactor Regulation 
 
Technical contact:  N. Fields, NRR
                    (301) 504-1173

Attachments:  
1.  Auto/Manual Reactor Trip Circuit Typical Train 
2.  List of Recently Issued NRC Information Notices
.
```

*Page Last Reviewed/Updated Wednesday, February 16, 2011*

#### Home

            - News Releases
            - Event Reports
            - ADAMS
            - Open Gov
            - Students & Teachers
            - Photos & Video

#### About Us

            - Strategic Plan
            - Budget & Performance
            - Perf & Accountability Rept
            - History of the NRC
            - Employment
            - NRC Ethics
            - Agency Status

#### Popular Documents

            - Info Digest
            - Factsheets & Brochures
            - Forms
            - Electronic Submittals
            - NRC Reports – NUREG
            - NRC Regulations – 10-CFR
            - Inspection Reports
            - Plain Writing
            - Enforcement Actions

#### Stay Connected

            - Twitter
            - YouTube
            - RSS
            - Blog

Regulations.govUSA.govRecoveryFOIANo Fear EEOInspector GeneralSite MapAccessibilityPrivacy PolicySite DisclaimerFor Employees