Facility _Information

facility _id utility

_code legal_owner_name

legl_operator_name

legal_address_type

legal_address

legal_city legal_state legal_zip 2830 15470 Duke Energy Ohio Duke Energy

Ohio legal owner139 East Fourth Street Cincinnati OH 45202 2832 15470 Duke Energy Ohio Duke Energy

Ohio legal owner139 East Fourth Street Cincinnati OH 45202 6019 15470 Duke Energy Ohio Duke Energy

Ohio legal owner139 East Fourth Street Cincinnati OH 45202

Page 1Facility _Information

plant_name

physical_address

phyical_city

physical_state

physical_zip

mailing_address

mailing_city

mailing_state

mailing_zip Walter C Beckjord

757 US Route 52

New Richmond

OH 45157 757 US Route 52 New Richmond

OH 45157 Miami Fort 11021 Brower Road North BendOH 45052 11021 Brower Road North BendOH 45052 W H Zimmer

1781 US Route 52

Moscow OH 45153 1781 US Route 52 Moscow OH 45153

Page 2Facility _Information

RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas TRUE TRUE FALSE FALSE FALSE TRUE TRUE FALSE No TRUE TRUE FALSE FALSE FALSE TRUE TRUE FALSE No TRUE TRUE FALSE FALSE FALSE TRUE TRUE FALSE

Page 3Facility _Information

ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note TRUE FALSE Noting instances of all deviations on quarterly excess emission reports; semi-annual deviation summary reports, quarterly

deviation reports. No Re: Unit/Boiler 5--Unit 5 consists of two boilers: Boiler 5-1 and 5-2, both exhausting to a stack common with Unit 6. All data for Unit 5 is reported for the combined output for both Unit 5 boilers.Re: Fields with dates--month is not known, so Month "01" was used.RE: ESP for Unit 4--Side A was brought online in 1958; Side B was brought online in 1974; for Unit 5--Side A was brought online in 1962 and rebuilt in 1992; Side B was brought onlinie in 1976; for unit 6--the original ESP wqs brought online in 1969 and was replaced by a new one in 1978.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Re: Pollutant for Sampling Run Details--There is no selection for Total PM, so we used PM (Filterable) in place of Total PM data.Emission test report U6032806 Run 1 actual flue gas temp was 325.6.Emission test report U6032806 Run 2 actual flue gas temp was 325.8 TRUE FALSE Noting instances of all deviations on quarterly excess emission reports; semi-annual deviation summary reports, quarterly

deviation reports. No Re: Retirement Data--Units 5-1 and 5-2 were retired on 12/31/2007.Re: Dates controls came online--where months are not known, "Month 01" was used.Part 1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Emission test U7022006, Run 1 flue gas temp was actually 302.Emission test U7022006, Run 2 flue gas temp was actually 305.Emission test U7022006, Run 3 flue gas temp was actually 306. FALSE FALSE Noting instances of all deviations on quarterly excess emission reports; semi-annual deviation summary reports. No The dates that the LNB and SCR came online have the correct year, but the month is unknown.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.

Page 4Facility _Information

Re: Unit/Boiler 5--Unit 5 consists of two boilers: Boiler 5-1 and 5-2, both exhausting to a stack common with Unit 6. All data for Unit 5 is reported for the combined output for both Unit 5 boilers.Re: Fields with dates--month is not known, so Month "01" was used.RE: ESP for Unit 4--Side A was brought online in 1958; Side B was brought online in 1974; for Unit 5--Side A was brought online in 1962 and rebuilt in 1992; Side B was brought onlinie in 1976; for unit 6--the original ESP wqs brought online in 1969 and was replaced by a new one in 1978.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Re: Pollutant for Sampling Run Details--There is no selection for Total PM, so we used PM (Filterable) in place of Total PM data.Emission test report U6032806 Run 1 actual flue gas temp was 325.6.Emission test report U6032806 Run 2 actual flue gas temp was 325.8 Re: Retirement Data--Units 5-1 and 5-2 were retired on 12/31/2007.Re: Dates controls came online--where months are not known, "Month 01" was used.Part 1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Emission test U7022006, Run 1 flue gas temp was actually 302.Emission test U7022006, Run 2 flue gas temp was actually 305.Emission test U7022006, Run 3 flue gas temp was actually 306. The dates that the LNB and SCR came online have the correct year, but the month is unknown.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.

Page 5Facility _Information

Re: Unit/Boiler 5--Unit 5 consists of two boilers: Boiler 5-1 and 5-2, both exhausting to a stack common with Unit 6. All data for Unit 5 is reported for the combined output for both Unit 5 boilers.Re: Fields with dates--month is not known, so Month "01" was used.RE: ESP for Unit 4--Side A was brought online in 1958; Side B was brought online in 1974; for Unit 5--Side A was brought online in 1962 and rebuilt in 1992; Side B was brought onlinie in 1976; for unit 6--the original ESP wqs brought online in 1969 and was replaced by a new one in 1978.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Re: Pollutant for Sampling Run Details--There is no selection for Total PM, so we used PM (Filterable) in place of Total PM data.Emission test report U6032806 Run 1 actual flue gas temp was 325.6.Emission test report U6032806 Run 2 actual flue gas temp was 325.8 Re: Retirement Data--Units 5-1 and 5-2 were retired on 12/31/2007.Re: Dates controls came online--where months are not known, "Month 01" was used.Part 1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Emission test U7022006, Run 1 flue gas temp was actually 302.Emission test U7022006, Run 2 flue gas temp was actually 305.Emission test U7022006, Run 3 flue gas temp was actually 306. The dates that the LNB and SCR came online have the correct year, but the month is unknown.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.

Page 6Facility _Information

Re: Unit/Boiler 5--Unit 5 consists of two boilers: Boiler 5-1 and 5-2, both exhausting to a stack common with Unit 6. All data for Unit 5 is reported for the combined output for both Unit 5 boilers.Re: Fields with dates--month is not known, so Month "01" was used.RE: ESP for Unit 4--Side A was brought online in 1958; Side B was brought online in 1974; for Unit 5--Side A was brought online in 1962 and rebuilt in 1992; Side B was brought onlinie in 1976; for unit 6--the original ESP wqs brought online in 1969 and was replaced by a new one in 1978.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Re: Pollutant for Sampling Run Details--There is no selection for Total PM, so we used PM (Filterable) in place of Total PM data.Emission test report U6032806 Run 1 actual flue gas temp was 325.6.Emission test report U6032806 Run 2 actual flue gas temp was 325.8 Re: Retirement Data--Units 5-1 and 5-2 were retired on 12/31/2007.Re: Dates controls came online--where months are not known, "Month 01" was used.Part 1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Emission test U7022006, Run 1 flue gas temp was actually 302.Emission test U7022006, Run 2 flue gas temp was actually 305.Emission test U7022006, Run 3 flue gas temp was actually 306. The dates that the LNB and SCR came online have the correct year, but the month is unknown.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.

Page 7Facility _Information

Re: Unit/Boiler 5--Unit 5 consists of two boilers: Boiler 5-1 and 5-2, both exhausting to a stack common with Unit 6. All data for Unit 5 is reported for the combined output for both Unit 5 boilers.Re: Fields with dates--month is not known, so Month "01" was used.RE: ESP for Unit 4--Side A was brought online in 1958; Side B was brought online in 1974; for Unit 5--Side A was brought online in 1962 and rebuilt in 1992; Side B was brought onlinie in 1976; for unit 6--the original ESP wqs brought online in 1969 and was replaced by a new one in 1978.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Re: Pollutant for Sampling Run Details--There is no selection for Total PM, so we used PM (Filterable) in place of Total PM data.Emission test report U6032806 Run 1 actual flue gas temp was 325.6.Emission test report U6032806 Run 2 actual flue gas temp was 325.8 Re: Retirement Data--Units 5-1 and 5-2 were retired on 12/31/2007.Re: Dates controls came online--where months are not known, "Month 01" was used.Part 1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Emission test U7022006, Run 1 flue gas temp was actually 302.Emission test U7022006, Run 2 flue gas temp was actually 305.Emission test U7022006, Run 3 flue gas temp was actually 306.

Page 8Facility _Information

Re: Unit/Boiler 5--Unit 5 consists of two boilers: Boiler 5-1 and 5-2, both exhausting to a stack common with Unit 6. All data for Unit 5 is reported for the combined output for both Unit 5 boilers.Re: Fields with dates--month is not known, so Month "01" was used.RE: ESP for Unit 4--Side A was brought online in 1958; Side B was brought online in 1974; for Unit 5--Side A was brought online in 1962 and rebuilt in 1992; Side B was brought onlinie in 1976; for unit 6--the original ESP wqs brought online in 1969 and was replaced by a new one in 1978.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Re: Pollutant for Sampling Run Details--There is no selection for Total PM, so we used PM (Filterable) in place of Total PM data.Emission test report U6032806 Run 1 actual flue gas temp was 325.6.Emission test report U6032806 Run 2 actual flue gas temp was 325.8 Re: Retirement Data--Units 5-1 and 5-2 were retired on 12/31/2007.Re: Dates controls came online--where months are not known, "Month 01" was used.Part 1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Emission test U7022006, Run 1 flue gas temp was actually 302.Emission test U7022006, Run 2 flue gas temp was actually 305.Emission test U7022006, Run 3 flue gas temp was actually 306.

Page 9Facility _Information

Re: Unit/Boiler 5--Unit 5 consists of two boilers: Boiler 5-1 and 5-2, both exhausting to a stack common with Unit 6. All data for Unit 5 is reported for the combined output for both Unit 5 boilers.Re: Fields with dates--month is not known, so Month "01" was used.RE: ESP for Unit 4--Side A was brought online in 1958; Side B was brought online in 1974; for Unit 5--Side A was brought online in 1962 and rebuilt in 1992; Side B was brought onlinie in 1976; for unit 6--the original ESP wqs brought online in 1969 and was replaced by a new one in 1978.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Re: Pollutant for Sampling Run Details--There is no selection for Total PM, so we used PM (Filterable) in place of Total PM data.Emission test report U6032806 Run 1 actual flue gas temp was 325.6.Emission test report U6032806 Run 2 actual flue gas temp was 325.8 Re: Retirement Data--Units 5-1 and 5-2 were retired on 12/31/2007.Re: Dates controls came online--where months are not known, "Month 01" was used.Part 1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Emission test U7022006, Run 1 flue gas temp was actually 302.Emission test U7022006, Run 2 flue gas temp was actually 305.Emission test U7022006, Run 3 flue gas temp was actually 306.

Page 10Facility _Information

Re: Unit/Boiler 5--Unit 5 consists of two boilers: Boiler 5-1 and 5-2, both exhausting to a stack common with Unit 6. All data for Unit 5 is reported for the combined output for both Unit 5 boilers.Re: Fields with dates--month is not known, so Month "01" was used.RE: ESP for Unit 4--Side A was brought online in 1958; Side B was brought online in 1974; for Unit 5--Side A was brought online in 1962 and rebuilt in 1992; Side B was brought onlinie in 1976; for unit 6--the original ESP wqs brought online in 1969 and was replaced by a new one in 1978.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Re: Pollutant for Sampling Run Details--There is no selection for Total PM, so we used PM (Filterable) in place of Total PM data.Emission test report U6032806 Run 1 actual flue gas temp was 325.6.Emission test report U6032806 Run 2 actual flue gas temp was 325.8

Page 11Facility _Information

Re: Unit/Boiler 5--Unit 5 consists of two boilers: Boiler 5-1 and 5-2, both exhausting to a stack common with Unit 6. All data for Unit 5 is reported for the combined output for both Unit 5 boilers.Re: Fields with dates--month is not known, so Month "01" was used.RE: ESP for Unit 4--Side A was brought online in 1958; Side B was brought online in 1974; for Unit 5--Side A was brought online in 1962 and rebuilt in 1992; Side B was brought onlinie in 1976; for unit 6--the original ESP wqs brought online in 1969 and was replaced by a new one in 1978.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Re: Pollutant for Sampling Run Details--There is no selection for Total PM, so we used PM (Filterable) in place of Total PM data.Emission test report U6032806 Run 1 actual flue gas temp was 325.6.Emission test report U6032806 Run 2 actual flue gas temp was 325.8

Page 12Facility _Information

Re: Unit/Boiler 5--Unit 5 consists of two boilers: Boiler 5-1 and 5-2, both exhausting to a stack common with Unit 6. All data for Unit 5 is reported for the combined output for both Unit 5 boilers.Re: Fields with dates--month is not known, so Month "01" was used.RE: ESP for Unit 4--Side A was brought online in 1958; Side B was brought online in 1974; for Unit 5--Side A was brought online in 1962 and rebuilt in 1992; Side B was brought onlinie in 1976; for unit 6--the original ESP wqs brought online in 1969 and was replaced by a new one in 1978.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Re: Pollutant for Sampling Run Details--There is no selection for Total PM, so we used PM (Filterable) in place of Total PM data.Emission test report U6032806 Run 1 actual flue gas temp was 325.6.Emission test report U6032806 Run 2 actual flue gas temp was 325.8

Page 13Facility _Information

Re: Unit/Boiler 5--Unit 5 consists of two boilers: Boiler 5-1 and 5-2, both exhausting to a stack common with Unit 6. All data for Unit 5 is reported for the combined output for both Unit 5 boilers.Re: Fields with dates--month is not known, so Month "01" was used.RE: ESP for Unit 4--Side A was brought online in 1958; Side B was brought online in 1974; for Unit 5--Side A was brought online in 1962 and rebuilt in 1992; Side B was brought onlinie in 1976; for unit 6--the original ESP wqs brought online in 1969 and was replaced by a new one in 1978.Part1: Guaranteed Emission Limits, Question 23“Guaranteed Emission Limits” are a contractual obligation and are not enforceable as a permit limit, or indicative of continued performance.Re: Pollutant for Sampling Run Details--There is no selection for Total PM, so we used PM (Filterable) in place of Total PM data.Emission test report U6032806 Run 1 actual flue gas temp was 325.6.Emission test report U6032806 Run 2 actual flue gas temp was 325.8

Page 14facility _contacts

facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 2830 7 GMIII-Non-Reg Fossil Station Dave P. Beck

5134195989 david.beck@duke-energy.com TRUE 2830 8 Environmental Coordinator Andrew R. Roebel

5134675032 andrew.roebel@duke-energy.com FALSE 2832 42 GM III-NonReg Fossil Station Michael Sharp

5134674936 michael.sharp@duke-energy.com TRUE 2832 43 Environmental Coordinator Ralph Wood

5134674886 jr.wood@duke-energy.com FALSE 6019 39 GMIII-Non-Reg Fossil Station David P. Beck

5134195989 david.beck@duke-energy.com TRUE 6019 40 Thomas W . Patt Environmental Coordinator

5134675212 tom.patt@duke-energy.com FALSE

Page 15facility _coal_utilized

facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note 2830 bituminous 100 100 2832 bituminous 100 100 2832 petroleum coke 0 0 6019 bituminous 100 100

Page 16facility _oil_utilized

facility _id oil_type percentage_volume percentage_btu

other_type 2830 No.2 Fuel Oil (distillate) 100 100 2832 No.2 Fuel Oil (distillate) 100 100 6019 No.2 Fuel Oil (distillate) 100 100

Page 17facility _other_materials

facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain

Page 18facility _other_materials

rcra_explain

Page 19boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuelheat_input max_heat_input MWe_capacity 2830 1 Tangential firing Dry Bottom coal 971 971 100 2830 2 Tangential firing Dry Bottom coal 999 999 100 2830 3 Wall firing - opposed firing Dry Bottom coal 1215 1215 135 2830 4 Tangential firing Dry Bottom coal 1423 1423 162 2830 5 Tangential firing Dry Bottom coal 2367 2367 255 2830 6 Tangential firing Dry Bottom coal 3979 3979 443 2832 Unit 6 Tangential firing Wet Bottom coal 1534 1253 175 2832 Unit 7 Wall firing - opposed firing Wet Bottom

coal 5025 4995 550 2832 Unit 8 Wall firing - opposed firing Wet Bottom

coal 5025 5003 550 6019 1 Wall firing - opposed firing Dry Bottom coal 12656 12656 1408

Page 20boiler_information

MWe_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 94 89.4 89.4 1650 1650 1005 1005 FALSE 1005 94 89.4 89.4 1650 1650 1005 1005 FALSE 1005 128 89.33 89.33 1850 1850 1005 1005 FALSE 1005 150 90.05 90.05 2725 2475 1005 1005 FALSE 1005 238 88.99 88.99 2500 2500 1005 1005 FALSE 1005 414 89.01 89.01 2500 2500 1005 1005 FALSE 1005 163 90.05 88.26 2725 2650 1055 1055 FALSE 1005 510 88.35 87.39 2925 2650 1005 1005 FALSE 1005 510 88.24 87.09 2925 2475 1005 1005 FALSE 1005 1300 88.52 86.7 3600 3600 1000 1000 FALSE 1000

Page 21boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 1005 6182 42.93 N FALSE FALSE 1005 5424 43.14 N FALSE FALSE 1005 5799 45.42 N FALSE FALSE 1005 7454 62.03 N FALSE FALSE 1005 5829 39.29 N FALSE FALSE 1005 6485 53.69 N FALSE FALSE 1005 8208 76.84 N FALSE FALSE 1005 7620 71.73 N FALSE FALSE 1005 7186 75.11 Subpart D FALSE FALSE 1000 8203 79.78 Subpart Da(1) FALSE

Page 22boiler_information

NOx_control

SO2_control

combustion_additives No Yes No No Yes No Yes Yes No Yes Yes No Yes Yes No Yes Yes No Yes No No Yes No No Yes Yes No Yes No No

Page 23boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 2830 1 coal - bituminous2007 0 99.87 2830 1 coal - bituminous2008 0 99.3 2830 1 coal - bituminous2009 0 99.67 2830 1 oil - distillate 2007 0 0.13 2830 1 oil - distillate 2008 0 0.7 2830 1 oil - distillate 2009 0 0.33 2830 2 coal - bituminous2007 0 99.72 2830 2 coal - bituminous2008 0 99.71 2830 2 coal - bituminous2009 0 99.7 2830 2 oil - distillate 2007 0 0.28 2830 2 oil - distillate 2008 0 0.29 2830 2 oil - distillate 2009 0 0.3 2830 3 coal - bituminous2007 0 99.68 2830 3 coal - bituminous2008 0 99.32 2830 3 coal - bituminous2009 0 99.47 2830 3 oil - distillate 2007 0 0.32 2830 3 oil - distillate 2008 0 0.68 2830 3 oil - distillate 2009 0 0.53 2830 4 coal - bituminous2007 0 99.63 2830 4 coal - bituminous2008 0 99.61 2830 4 coal - bituminous2009 0 99.71 2830 4 oil - distillate 2007 0 0.37 2830 4 oil - distillate 2008 0 0.39 2830 4 oil - distillate 2009 0 0.29 2830 5 coal - bituminous2007 0 99.8 2830 5 coal - bituminous2008 0 99.46 2830 5 coal - bituminous2009 0 99.6 2830 5 oil - distillate 2007 0 0.2 2830 5 oil - distillate 2008 0 0.54 2830 5 oil - distillate 2009 0 0.4 2830 6 coal - bituminous2007 0 99.86 2830 6 coal - bituminous2008 0 99.55 2830 6 coal - bituminous2009 0 99.9 2830 6 oil - distillate 2007 0 0.14 2830 6 oil - distillate 2008 0 0.45 2830 6 oil - distillate 2009 0 0.1 2832 Unit 6 coal - bituminous2007 0 99.7 2832 Unit 6 coal - bituminous2008 0 99.8 2832 Unit 6 coal - bituminous2009 0 99.8 2832 Unit 6 oil - distillate 2007 0 0.3 2832 Unit 6 oil - distillate 2008 0 0.2 2832 Unit 6 oil - distillate 2009 0 0.2 2832 Unit 7 coal - bituminous2007 0 99.2 2832 Unit 7 coal - bituminous2008 0 99.6 2832 Unit 7 coal - bituminous2009 0 99.5 2832 Unit 7 oil - distillate 2007 0 0.8 2832 Unit 7 oil - distillate 2008 0 0.4 2832 Unit 7 oil - distillate 2009 0 0.5 2832 Unit 8 coal - bituminous2007 0 99.5 2832 Unit 8 coal - bituminous2008 0 99.7 2832 Unit 8 coal - bituminous2009 0 99.7

Page 24boiler_fuels

2832 Unit 8 oil - distillate 2007 0 0.5 2832 Unit 8 oil - distillate 2008 0 0.3 2832 Unit 8 oil - distillate 2009 0 0.3 6019 1 coal - bituminous2007 0 94 6019 1 coal - bituminous2008 0 94 6019 1 coal - bituminous2009 0 94 6019 1 oil - distillate 2007 0 6 6019 1 oil - distillate 2008 0 6 6019 1 oil - distillate 2009 0 6

Page 25boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online 2830 3 Low NOx Burner 1/1/2004 2830 3 Overfire Air 1/1/2004 2830 4 Low NOx Burner 1/1/2004 2830 4 Overfire Air 1/1/2004 2830 5 Low NOx Burner 1/1/1993 2830 5 Overfire Air 1/1/1993 2830 6 Low NOx Burner 1/1/1994 2830 6 Overfire Air 1/1/1994 2832 Unit 6 Low NOx Burner 1/1/2006 2832 Unit 7 Low NOx Burner 3/1/1998 2832 Unit 8 Low NOx Burner 1/1/1978 6019 1 Low NOx Burner 1/1/1991

Page 26boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online 2830 1 Low Sulfur Fuel Oil 1/1/2008 2830 2 Low Sulfur Fuel Oil 1/1/2008 2830 3 Low Sulfur Fuel Oil 1/1/2008 2830 4 Low Sulfur Fuel Oil 1/1/2008 2830 5 Low Sulfur Fuel Oil 1/1/2008 2830 6 Low Sulfur Fuel Oil 1/1/2008 2832 Unit 8 Low Sulfur Coal 1/1/1974

Page 27boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 28facility _units

facility _id unit_id 2830 UNIT1 2830 UNIT2 2830 UNIT3 2830 UNIT4 2830 UNIT5 2830 UNIT6 2832 Unit 6 2832 Unit 7 2832 Unit 8 6019 UNIT1

Page 29unit_boilers

facility _id unit_id boiler_id 2830 UNIT1 1 2830 UNIT2 2 2830 UNIT3 3 2830 UNIT4 4 2830 UNIT5 5 2830 UNIT6 6 2832 Unit 6 Unit 6 2832 Unit 7 Unit 7 2832 Unit 8 Unit 8 6019 UNIT1 1

Page 30facility _controls

facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 2830 WCBESPU1

PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 1/1/1972 2830 WCBU2ESP

PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 1/1/1973 2830 WCBU3ESP

PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 1/1/1971 2830 WCBU4ESP

PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 1/1/1974 2830 WCBU5ESP

PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 1/1/1976 2830 WCBU6ESP

PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 1/1/1978 2832 MFSU6ESP

PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 11/1/1960 2832 MFSU7ESP

PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 5/1/1975 2832 MFSU7FGD

SO2 control

Spray type FALSE 1/1/2007 2832 MFSU7SCR

NOx control

Selective Cataly

tic Reduction FALSE 1/1/2007 Ammonia 2832 MFSU7SO3

Other control

Dry sorbent injection FALSE 1/1/2007 2832 MFSU8ESP

PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 2/1/1978 2832 MFSU8FGD

SO2 control

Spray type FALSE 1/1/2007 2832 MFSU8SCR

NOx control

Selective Cataly

tic Reduction FALSE 1/1/2001 Ammonia 2832 MFSU8SO3

Other control

Dry sorbent injection FALSE 1/1/2007 6019 DSI1 Other control Dry sorbent injection FALSE 5/1/2004 6019 ESP1 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 3/1/1991 6019 FGD1 SO2 control FALSE 6/1/2004 6019 MGOH INJ Other control Other (specify)

Magnesium Hydroxide Injection

FALSE 6019 SCR1 NOx control Selective Cataly

tic Reduction FALSE 1/1/2004 Ammonia

Page 31facility _controls

reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive

Limestone NO

Limestone NO

Calcium carbide slurry

Page 32facility _sampling_ports

facility _id sampling_port_id 2832 U7FGDIN 2832 U8FGDIN

Page 33facility _stacks

facility _id stack_id stack_height stack_diameter

sack_gas_velocity 2830 WCB STK1 2830 WCB STK2 2830 WCB STK4 2830 WCB STK5,6 2830 WCBSTK3 2832 MFSU56STACK 2832 MFSU7STACK 2832 MFSU8STACK 6019 ZIM STK1

Page 34configurations

facility _id configuration_id 2830 1 2830 2 2830 3 2830 4 2830 5 2830 6 2832 U6 2832 U7 2832 U8 6019 1

Page 35configuration_components

facility _id configuration_id

component_id

order component_type port_near 2830 1 UNIT1 1 Unit 2830 1 WCB STK1 3 Stack 2830 1 WCBESPU1 2 PM control 2830 2 UNIT2 1 Unit 2830 2 WCB STK2 3 Stack 2830 2 WCBU2ESP 2 PM control 2830 3 UNIT3 1 Unit 2830 3 WCBSTK3 3 Stack 2830 3 WCBU3ESP 2 PM control 2830 4 UNIT4 1 Unit 2830 4 WCB STK4 3 Stack 2830 4 WCBU4ESP 2 PM control 2830 5 UNIT5 1 Unit 2830 5 WCB STK5,6 3 Stack 2830 5 WCBU5ESP 2 PM control 2830 6 UNIT6 1 Unit 2830 6 WCB STK5,6 3 Stack 2830 6 WCBU6ESP 2 PM control 2832 U6 MFSU56STACK 3 Stack 2832 U6 MFSU6ESP 2 PM control 2832 U6 Unit 6 1 Unit 2832 U7 MFSU7ESP 6 PM control 2832 U7 MFSU7FGD 4 SO2 control 2832 U7 MFSU7SCR 2 NOx control 2832 U7 MFSU7SO3 5 Other control 2832 U7 MFSU7STACK 7 Stack 2832 U7 U7FGDIN 3 Sampling Port next 2832 U7 Unit 7 1 Unit 2832 U8 MFSU7SCR 2 NOx control 2832 U8 MFSU8ESP 6 PM control 2832 U8 MFSU8FGD 4 SO2 control 2832 U8 MFSU8SO3 5 Other control 2832 U8 MFSU8STACK 7 Stack 2832 U8 U8FGDIN 3 Sampling Port next 2832 U8 Unit 8 1 Unit 6019 1 DSI1 4 Other control 6019 1 ESP1 5 PM control 6019 1 FGD1 6 SO2 control 6019 1 MGOH INJ 2 Other control 6019 1 SCR1 3 NOx control 6019 1 UNIT1 1 Unit 6019 1 ZIM STK1 7 Stack

Page 36configuration_pollutants1

facility _id configuration_id

pollutant_name

permit_type_1

emlimit_1 emlimit_units_1 avg_period_1

emlimit_2 emlimit_units_2 2832 U6 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

Continuous 2832 U6 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

5 pound per million British Thermal Unit (lb/MMBtu)

30 days 2832 U7 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

Continuous 2832 U7 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

2.37 pound per million British Thermal Unit (lb/MMBtu)

30 days 5.5 pound per million British Thermal Unit (lb/MMBtu) 2832 U8 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

Continuous 2832 U8 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1.2 pound per million British Thermal Unit (lb/MMBtu)

30 days 2832 U8 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.7 pound per million British Thermal Unit (lb/MMBtu)

3 hours 6019 1 PM (Filterable) Fderal - Title V Operating Permit

0.025 pound per million British Thermal Unit (lb/MMBtu) 1310 tons per year (tons/yr) 6019 1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

0.548 pound per million British Thermal Unit (lb/MMBtu) 1 pound per million British Thermal Unit (lb/MMBtu) 6019 1 Carbon Monoxide (CO) Federal - PSD Permit

1406 tons per year (tons/yr) 2830 1 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

Continuous 2830 1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1.84 pound per million British Thermal Unit (lb/MMBtu)

30 days 2830 2 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

Continuous 2830 2 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1.84 pound per million British Thermal Unit (lb/MMBtu)

30 days 2830 3 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

Continuous 2830 3 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1.84 pound per million British Thermal Unit (lb/MMBtu)

30 days 2830 4 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

Continuous 2830 4 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1.84 pound per million British Thermal Unit (lb/MMBtu)

30 days 2830 5 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

Continuous 2830 5 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

7.19 pound per million British Thermal Unit (lb/MMBtu)

30 days 2830 6 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

Continuous 2830 6 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

7.19 pound per million British Thermal Unit (lb/MMBtu)

30 days

Page 37configuration_pollutants1

avg_period_2

emlim it_3 emlim it_units_3 avg_period_3

emlimit_4 emlimit_units_4 avg_period_4

emlimit_details

test_method

SO2 Limit is based on a 30-day rolling average

30 days Emission Limit 2 applies only when not operating the FGD unit.

Compliance is based on 3-hour rolling average tons per year (tons/yr) Method 5B pound per million British Thermal Unit (lb/MMBtu) 28726 tons per year (tons/yr) Permit limit 1 based on CEM data. Permit limit 2 based on Method 6 Stack Test.

Method 5 Compliance with SO2 limit is based on 30-day rolling average Method 5 Compliance with SO2 limit is based on 30-day rolling average Method 5 Compliance with SO2 limit is based on 30-day rolling average Method 5 Compliance with SO2 limit is based on 30-day rolling average Method 5 Compliance with SO2 limit is based on 30-day rolling average Method 5 Compliance with SO2 limit is based on 30-day rolling average

Page 38configuration_pollutants1

emrate emrate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping

req_reporting No Stack Tests and COMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. SO2 Limit is based on a 30-day rolling average

No Stack Tests and CEMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. No Stack Tests and COMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Emission Limit 2 applies only when not operating the FGD unit.

No Stack Tests and CEMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. No Stack tests and COMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. No Stack tests and CEMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Compliance is based on 3-hour rolling average No Stack tests and CEMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. No Stack tests and COMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Permit limit 1 based on CEM data. Permit limit 2 based on Method 6 Stack Test. No Stack tests and COMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. No N/A Maintain all records for 5 years Excess Emission reports, Deviation reports, Compliance certifications. No Stack Tests and COMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Compliance with SO2 limit is based on 30-day rlling average No Stack Tests and CEMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. No Stack Tests and COMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Compliance with SO2 limit is based on 30-day rlling average No Stack Tests and CEMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. No Stack Tests and COMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Compliance with SO2 limit is based on 30-day rlling average No Stack Tests and CEMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. No Stack Tests and COMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Compliance with SO2 limit is based on 30-day rlling average No Stack Tests and CEMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. No Stack Tests and COMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Compliance with SO2 limit is based on 30-day rlling average No Stack Tests and CEMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. No Stack Tests and COMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Compliance with SO2 limit is based on 30-day rlling average No Stack Tests and CEMS Maintain all records for 5 years

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications.

Page 39configuration_pollutants1

Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Excess Emission reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications. Stack test reports, Excess Emission reports, Monitor Downtime reports, Deviation reports, Compliance certifications.

Page 40control_technologies

facility _id configuration_id

component_id

control_id project_titleproject_type vendor_name

vndor_contact

vendor_phone 2832 U6 MFSU6ESP 1 Trial of Amended Silicates (TM) Sorbent for Mercury Control at Miami Fort Station: A Utility Perspec Demonstration

ADA Technologies, Inc.

James R. Butz

3037925615

Page 41control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive 8100 Shaffer Parkway

Littleton CO 80127 1/1/2006 3/1/2006 Amended Silicates (TM)

Page 42control_technologies

injection_point

HAP_emission_reduction

HAP_emission_rate

HAP_emission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units Amended Silicates (TM)

Page 43control_technologies

feed_rate_units

Page 44control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type 2832 U6 MFSU6ESP 1 bituminous

Page 45control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_name 2832 U6 MFSU6ESP 1 Total Mercury (Hgt)

Page 46control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investment

total_operating_costs

base_year 2832 U6 MFSU6ESP 1 Yes No 2006

Page 47control_costs

CBI FALSE

Page 48misc_controls

facility _id misc_control_id

control_description

Page 49misc_control_configurations

facility _id misc_control_id

configuration_id

Page 50fuel_shipments

facility _id shipment_id

shipment_date

amount_received

amount_units

fuel_type state_country other_country

county

Page 51fuel_shipments

coal_seam shipment_method

Page 52fuel_shipment_configurations

facility _id shipment_id

configuration_id

Page 53fuel_shipment_samples

facility _id shipment_id

sample_id amount_fuel amount_fuel_units

total_sulfur ash_content heating_value

hating_units

Page 54fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address

Page 55fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_name lab_address lab_city lab_state lab_zip analysis_copies

Page 56fuel_shipment_samples

analysis_copies

Page 57fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL

Page 58test_reports

facility _id report_id report_typeother_type report_description report_begin_date

report_end_date

before_control

during_deviation 2830 U1110706 compliance Stack testing 11/7/2006 No No 2830 U1111605 compliance Stack testing ######## No No 2830 U1120109 compliance Stack testing 12/1/2009 No No 2830 U1120407 compliance Stack testing 12/4/2007 No No 2830 U1121108 compliance Stack testing ######## No No 2830 U2021908 compliance Stack testing 2/19/2008 No No 2830 U2022108 compliance Stack testing 2/21/2008 No No 2830 U2042506 compliance Stack testing 4/25/2006 No No 2830 U2051806 compliance Stack testing 5/18/2006 No No 2830 U2052406 compliance Stack testing 5/24/2006 No No 2830 U2052506 compliance Stack testing 5/25/2006 No No 2830 U2060607 compliance Stack testing 6/6/2007 No No 2830 U2062806 compliance Stack testing 6/28/2006 No No 2830 U3120507 compliance Stack testing 12/5/2007 No No 2830 U4022008 compliance Stack testing 2/20/2008 No No 2830 U4091305 compliance Stack testing 9/13/2005 No No 2830 U5033008 compliance Stack testing 5/30/2008 No No 2830 U5101105 compliance Stack testing ######## No No 2830 U6032806 compliance Stack testing 3/28/2006 No No 2832 U6030306 compliance Stack testing 3/3/2006 No No 2832 U6032708 compliance Stack testing 3/27/2008 No No 2832 U7032006 compliance Stack testing 3/20/2006 No No 2832 U7042908 compliance Stack testing 4/29/2008 4/30/2008 No No 2832 U7050108 compliance Stack testing 5/1/2008 5/2/2008 No No 2832 U7050808 compliance Stack testing 5/8/2008 5/9/2008 No No 2832 U7052008 compliance Stack testing 5/20/2008 No No 2832 U7052208FGD

compliance SO2 removal testing-this report is the same as U7052208-post-FGD SO2 5/22/2008 No No 2832 U7052208FGDIN

compliance SO2 removakl testing 5/22/2008 Yes No 2832 U8032106 compliance Stack testing 3/21/2006 No No 2832 U8082907 compliance Stack testing 8/29/2007 No No 2832 U8082907FGD

compliance SO2 removal testing-same test as U7082907FGDIN. This is report on post-FGD SO2. 8/29/2007 No No 2832 U8082907FGDIN

compliance SO2 removal testing 8/29/2007 Yes No 2832 U8083007FGD

compliance SO2 removal testing-this report is same as U8083007--post-FGD SO2 8/30/2007 No No 2832 U8083007FGDIN

compliance SO2 removal testing 8/30/2007 Yes No 6019 U1 112007 compliance Stack testing ######## No No 6019 U1041205 compliance Stack testing 4/12/2005 No No 6019 U1072809 compliance Stack testing 7/28/2009 No No 6019 U1101508 other Hg testing Hg testing ######## No No

Page 59test_reports

deviation_reports No No No No No No No No No No No No No No No No No No No No No No No No No No No No No No No No No No No No No No

Page 60test_report_configurations

facility _id report_id configuration_id 2830 U1110706 1 2830 U1111605 1 2830 U1120109 1 2830 U1120407 1 2830 U1121108 1 2830 U2021908 2 2830 U2022108 2 2830 U2042506 2 2830 U2051806 2 2830 U2052406 2 2830 U2052506 2 2830 U2060607 2 2830 U2062806 2 2830 U3120507 3 2830 U4022008 4 2830 U4091305 4 2830 U5033008 5 2830 U5101105 5 2830 U6032806 6 2832 U6030306 U6 2832 U6032708 U6 2832 U7032006 U7 2832 U7042908 U7 2832 U7050108 U7 2832 U7050808 U7 2832 U7052008 U7 2832 U7052208FGD

U8 2832 U7052208FGDIN

U7 2832 U8032106 U8 2832 U8082907 U8 2832 U8082907FGD

U7 2832 U8082907FGDIN

U8 2832 U8083007FGD

U8 2832 U8083007FGDIN

U8 6019 U1 112007 1 6019 U1041205 1 6019 U1072809 1 6019 U1101508 1

Page 61test_report_fuels

facility _id report_id fuel_id 2830 U1110706 COAL 2830 U1111605 COAl 2830 U1120109 COAL 2830 U1120407 COAL 2830 U1121108 COAL 2830 U2021908 COAL 2830 U2022108 COAL 2830 U2042506 COAL 2830 U2051806 COAL 2830 U2052406 COAL 2830 U2052506 COAL 2830 U2060607 COAL 2830 U2062806 COAL 2830 U3120507 COAL 2830 U4022008 COAL 2830 U4091305 COAL 2830 U5033008 COAL 2830 U5101105 COAL 2830 U6032806 COAL 2832 U6030306 COAL 2832 U6032708 COAL 2832 U7032006 COAL 2832 U7042908 COAL 2832 U7050108 COAL 2832 U7050808 COAL 2832 U7052008 COAL 2832 U7052208FGD

COAL 2832 U7052208FGDIN

COAL 2832 U8032106 COAL 2832 U8082907 COAL 2832 U8082907FGD

COAL 2832 U8082907FGDIN

COAL 2832 U8083007FGD

COAL 2832 U8083007FGDIN

COAL 6019 U1 112007 COAL 6019 U1041205 COAL 6019 U1072809 COAL 6019 U1101508 COAL

Page 62test_report_fuel_types

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 2830 U1110706 COAL coal - bituminous 100 100 2830 U1111605 COAl coal - bituminous 100 100 2830 U1120109 COAL coal - bituminous 100 100 2830 U1120407 COAL coal - bituminous 100 100 2830 U1121108 COAL coal - bituminous 100 100 2830 U2021908 COAL coal - bituminous 100 100 2830 U2022108 COAL coal - bituminous 100 100 2830 U2042506 COAL coal - bituminous 100 100 2830 U2051806 COAL coal - bituminous 100 100 2830 U2052406 COAL coal - bituminous 100 100 2830 U2052506 COAL coal - bituminous 100 100 2830 U2060607 COAL coal - bituminous 100 100 2830 U2062806 COAL coal - bituminous 100 100 2830 U3120507 COAL coal - bituminous 100 100 2830 U4022008 COAL coal - bituminous 100 100 2830 U4091305 COAL coal - bituminous 100 100 2830 U5033008 COAL coal - bituminous 100 100 2830 U5101105 COAL coal - bituminous 100 100 2830 U6032806 COAL coal - bituminous 100 100 2832 U6030306 COAL coal - bituminous 100 100 2832 U6032708 COAL coal - bituminous 100 100 2832 U7032006 COAL coal - bituminous 100 100 2832 U7042908 COAL coal - bituminous 100 100 2832 U7050108 COAL coal - bituminous 100 100 2832 U7050808 COAL coal - bituminous 100 100 2832 U7052008 COAL coal - bituminous 100 100 2832 U7052208FGD

COAL coal - bituminous 100 100 2832 U7052208FGDIN

COAL coal - bituminous 100 100 2832 U8032106 COAL coal - bituminous 100 100 2832 U8082907 COAL coal - bituminous 100 100 2832 U8082907FGD

COAL coal - bituminous 100 100 2832 U8082907FGDIN

COAL coal - bituminous 100 100 2832 U8083007FGD

COAL coal - bituminous 100 100 2832 U8083007FGDIN

COAL coal - bituminous 100 100 6019 U1 112007 COAL coal - bituminous 100 100 6019 U1041205 COAL coal - bituminous 100 100 6019 U1072809 COAL coal - bituminous 100 100 6019 U1101508 COAL coal - bituminous 100 100

Page 63cem_data

facility _id time_period

cem_period_description

Page 64cem_data_pollutants1

facility _id time_period

pollutant_name

Page 65test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_bypass_percent

testing_bypass_percent 2830 U1110706 WCB STK1 No No 2830 U1111605 WCB STK1 No No 2830 U1120109 WCB STK1 No No 2830 U1120407 WCB STK1 No No 2830 U1121108 WCB STK1 No No 2830 U2021908 WCB STK2No No 2830 U2022108 WCB STK2No No 2830 U2042506 WCB STK2No No 2830 U2051806 WCB STK2No No 2830 U2052406 WCB STK2No No 2830 U2052506 WCB STK2No No 2830 U2060607 WCB STK2No No 2830 U2062806 WCB STK2No No 2830 U3120507 WCBSTK3 No No 2830 U4022008 WCB STK4No No 2830 U4091305 WCB STK4No No 2830 U5033008 WCB STK5,6 No No 2830 U5101105 WCB STK5,6 No No 2830 U6032806 WCB STK5,6 No No 2832 U6030306 MFSU56STACK No No 2832 U6032708 MFSU56STACK No No 2832 U7032006 MFSU7STACK No No 2832 U7042908 MFSU7STACK No No 2832 U7050108 MFSU7STACK No No 2832 U7050808 MFSU7STACK No No 2832 U7052008 MFSU7STACK No No 2832 U7052208FGD

MFSU7STACK

No No 2832 U7052208FGDIN

U7FGDIN No Yes D 0 0 2832 U8032106 MFSU8STACK No No 2832 U8082907 MFSU8STACK No No 2832 U8082907FGD

MFSU7STACK

No No 2832 U8082907FGDIN

U7FGDIN No Yes D 0 0 2832 U8083007FGD

MFSU8STACK

No No 2832 U8083007FGDIN

U8FGDIN No Yes D 0 0 6019 U1 112007 ZIM STK1 No No 6019 U1041205 ZIM STK1 No No 6019 U1072809 ZIM STK1 No No 6019 U1101508 ZIM STK1 No No

Page 66test_report_sampling

fg_fraction

Page 67sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetime

unit_load net_generation fg_moisture_content 2830 U1110706 WCB STK1 1 11/7/2006 11/7/2006 98 7.23 2830 U1110706 WCB STK12 11/7/2006 11/7/2006 100 7 2830 U1110706 WCB STK13 11/7/2006 11/7/2006 100 7.35 2830 U1111605 WCB STK1 1 ######## ######## 100 6.36 2830 U1111605 WCB STK12 ######## ######## 100 6.72 2830 U1111605 WCB STK13 ######## ######## 100 7.05 2830 U1120109 WCB STK1 1 12/1/2009 12/1/2009 91 5.67 2830 U1120109 WCB STK12 12/1/2009 12/1/2009 90 5.84 2830 U1120109 WCB STK13 12/1/2009 12/1/2009 89 5.91 2830 U1120109 WCB STK14 12/1/2009 12/1/2009 89 5.67 2830 U1120407 WCB STK1 1 12/4/2007 12/4/2007 100 6.6 2830 U1120407 WCB STK12 12/4/2007 12/4/2007 100 6.79 2830 U1120407 WCB STK13 12/4/2007 12/4/2007 99 6.46 2830 U1121108 WCB STK1 1 ######## ######## 96 6.26 2830 U1121108 WCB STK12 ######## ######## 96 6.03 2830 U1121108 WCB STK13 ######## ######## 94 6.56 2830 U2021908 WCB STK21 2/19/2008 2/19/2008 99 8.37 2830 U2021908 WCB STK2 2 2/19/2008 2/19/2008 99 5.63 2830 U2021908 WCB STK2 3 2/19/2008 2/19/2008 99 6.94 2830 U2022108 WCB STK21 2/21/2008 2/21/2008 428 8.61 2830 U2022108 WCB STK2 2 2/21/2008 2/21/2008 425 8.84 2830 U2022108 WCB STK2 3 2/21/2008 2/21/2008 425 8.7 2830 U2042506 WCB STK21 4/25/2006 4/25/2006 101 4.94 2830 U2042506 WCB STK2 2 4/25/2006 4/25/2006 100 5.4 2830 U2042506 WCB STK2 3 4/25/2006 4/25/2006 100 5.47 2830 U2051806 WCB STK21 5/18/2006 5/18/2006 80 4.06 2830 U2051806 WCB STK2 2 5/18/2006 5/18/2006 80 4.82 2830 U2051806 WCB STK2 3 5/18/2006 5/18/2006 80 4.78 2830 U2052406 WCB STK21 5/24/2006 5/24/2006 80 6.78 2830 U2052406 WCB STK2 2 5/24/2006 5/24/2006 80 6.93 2830 U2052406 WCB STK2 3 5/24/2006 5/24/2006 90 6.64 2830 U2052406 WCB STK2 4 5/24/2006 5/24/2006 90 6.59 2830 U2052506 WCB STK21 5/25/2006 5/25/2006 95 7.72 2830 U2052506 WCB STK2 2 5/25/2006 5/25/2006 95 7.8 2830 U2052506 WCB STK2 3 5/25/2006 5/25/2006 100 7.64 2830 U2052506 WCB STK2 4 5/25/2006 5/25/2006 100 8.27 2830 U2052506 WCB STK2 5 5/25/2006 5/25/2006 100 7.38 2830 U2060607 WCB STK21 6/6/2007 6/6/2007 97 6.48 2830 U2060607 WCB STK2 2 6/6/2007 6/6/2007 97 7.1 2830 U2060607 WCB STK2 3 6/6/2007 6/6/2007 97 6.42 2830 U2062806 WCB STK21 6/28/2006 6/28/2006 100 6.01 2830 U2062806 WCB STK2 2 6/28/2006 6/28/2006 99 4.77 2830 U2062806 WCB STK2 3 6/28/2006 6/28/2006 100 5.03 2830 U3120507 WCBSTK3 1 12/5/2007 12/5/2007 135 6.77 2830 U3120507 WCBSTK3 2 12/5/2007 12/5/2007 136 7.27 2830 U3120507 WCBSTK3 3 12/5/2007 12/5/2007 135 6.64 2830 U4022008 WCB STK41 2/20/2008 2/20/2008 163 6.19 2830 U4022008 WCB STK4 2 2/20/2008 2/20/2008 164 6.31 2830 U4022008 WCB STK4 3 2/20/2008 2/20/2008 164 5.96 2830 U4091305 WCB STK41 9/13/2005 9/13/2005 156 5.6 2830 U4091305 WCB STK4 2 9/13/2005 9/13/2005 158 6.17

Page 68sampling_runs

2830 U4091305 WCB STK4 3 9/13/2005 9/13/2005 155 5.91 2830 U5033008 WCB STK5,6 1 5/30/2008 5/30/2008 255 9.65 2830 U5033008 WCB STK5,6 2 5/30/2008 5/30/2008 253 9.38 2830 U5033008 WCB STK5,6 3 5/30/2008 5/30/2008 251 9.72 2830 U5101105 WCB STK5,6 1 ######## ######## 255 7.87 2830 U5101105 WCB STK5,6 2 ######## ######## 255 7.19 2830 U5101105 WCB STK5,6 3 ######## ######## 254 8.26 2830 U6032806 WCB STK5,6 1 3/28/2006 3/28/2006 433 6.05 2830 U6032806 WCB STK5,6 2 3/28/2006 3/28/2006 433 6.81 2830 U6032806 WCB STK5,6 3 3/28/2006 3/28/2006 434 6.59 2832 U6030306 MFSU56STACK 1 3/3/2006 3/3/2006 174.2 4.99 2832 U6030306 MFSU56STACK 2 3/3/2006 3/3/2006 173.8 5.42 2832 U6030306 MFSU56STACK 3 3/3/2006 3/3/2006 172 4.08 2832 U6032708 MFSU56STACK 1 3/27/2008 3/27/2008 169 7.19 2832 U6032708 MFSU56STACK 2 3/27/2008 3/27/2008 169 6.56 2832 U6032708 MFSU56STACK 3 3/27/2008 3/27/2008 170 7.43 2832 U7032006 MFSU7STACK 1 3/20/2006 3/20/2006 525 6.99 2832 U7032006 MFSU7STACK 2 3/20/2006 3/20/2006 525 7.57 2832 U7032006 MFSU7STACK 3 3/20/2006 3/20/2006 525 6.39 2832 U7042908 MFSU7STACK 1 4/29/2008 4/29/2008 551 15.21 2832 U7042908 MFSU7STACK 2 4/29/2008 4/29/2008 551 15.93 2832 U7042908 MFSU7STACK 3 4/29/2008 4/29/2008 551 16.57 2832 U7042908 MFSU7STACK 4 4/29/2008 4/29/2008 551 14.16 2832 U7042908 MFSU7STACK 5 4/30/2008 4/30/2008 2832 U7042908 MFSU7STACK 6 4/30/2008 4/30/2008 551 14.58 2832 U7050108 MFSU7STACK 1 5/1/2008 5/1/2008 551 15.11 2832 U7050108 MFSU7STACK 2 5/1/2008 5/1/2008 551 14.89 2832 U7050108 MFSU7STACK 3 5/1/2008 5/1/2008 551 14.72 2832 U7050108 MFSU7STACK 4 5/2/2008 5/2/2008 551 14.56 2832 U7050808 MFSU7STACK 1 5/8/2008 5/8/2008 551 15.11 2832 U7050808 MFSU7STACK 2 5/8/2008 5/8/2008 551 12.71 2832 U7050808 MFSU7STACK 3 5/8/2008 5/8/2008 51 13.22 2832 U7050808 MFSU7STACK 4 5/9/2008 5/9/2008 551 15.04 2832 U7052008 MFSU7STACK 1 5/20/2008 5/20/2008 550 14.34 2832 U7052008 MFSU7STACK 2 5/20/2008 5/20/2008 550 15.76 2832 U7052008 MFSU7STACK 3 5/20/2008 5/20/2008 550 13.74 2832 U7052208FGD

MFSU7STACK

1 5/22/2008 5/22/2008 2832 U7052208FGD

MFSU7STACK

2 5/22/2008 5/22/2008 2832 U7052208FGD

MFSU7STACK

3 5/22/2008 5/22/2008 2832 U7052208FGDIN

U7FGDIN 1 5/22/2008 5/22/2008 2832 U7052208FGDIN

U7FGDIN 2 5/22/2008 5/22/2008 2832 U7052208FGDIN

U7FGDIN 3 5/22/2008 5/22/2008 2832 U8032106 MFSU8STACK 1 3/21/2006 3/21/2006 526 7.19 2832 U8032106 MFSU8STACK 2 3/21/2006 3/21/2006 527 6.81 2832 U8032106 MFSU8STACK 3 3/21/2006 3/21/2006 524 6 2832 U8082907 MFSU8STACK 1 8/29/2007 8/29/2007 556 15.13 2832 U8082907 MFSU8STACK 2 8/29/2007 8/29/2007 556 15.13 2832 U8082907 MFSU8STACK 3 8/29/2007 8/29/2007 555 15.28 2832 U8082907FGD

MFSU7STACK

1 8/29/2007 8/29/2007 2832 U8082907FGD

MFSU7STACK

2 8/29/2007 8/29/2007 2832 U8082907FGD

MFSU7STACK

3 8/29/2007 8/29/2007 2832 U8082907FGDIN

U7FGDIN 1 8/29/2007 8/29/2007 556 15.13

Page 69sampling_runs

2832 U8082907FGDIN

U7FGDIN 2 8/29/2007 8/29/2007 556 15.13 2832 U8082907FGDIN

U7FGDIN 3 8/29/2007 8/29/2007 555 15.28 2832 U8083007FGD

MFSU8STACK

1 8/30/2007 8/30/2007 2832 U8083007FGD

MFSU8STACK

2 8/30/2007 8/30/2007 2832 U8083007FGD

MFSU8STACK

3 8/30/2007 8/30/2007 2832 U8083007FGDIN

U8FGDIN 1 8/30/2007 8/30/2007 2832 U8083007FGDIN

U8FGDIN 2 8/30/2007 8/30/2007 2832 U8083007FGDIN

U8FGDIN 3 8/30/2007 8/30/2007 6019 U1 112007 ZIM STK1 1 ######## ######## 1418.5 15 6019 U1 112007 ZIM STK1 2 ######## ######## 1415.6 14.66 6019 U1 112007 ZIM STK1 3 ######## ######## 1420.1 13.73 6019 U1041205 ZIM STK1 1 4/12/2005 4/12/2005 1409 8.07 6019 U1041205 ZIM STK1 2 4/12/2005 4/12/2005 1408.6 8.07 6019 U1041205 ZIM STK1 3 4/12/2005 4/12/2005 1407 8.25 6019 U1072809 ZIM STK1 1 7/28/2009 7/28/2009 1403.6 11.5 6019 U1072809 ZIM STK1 2 7/28/2009 7/28/2009 1402.2 13.67 6019 U1072809 ZIM STK1 3 7/28/2009 7/28/2009 1406.5 13.21 6019 U1101508 ZIM STK1 1 ######## ######## 6019 U1101508 ZIM STK1 2 ######## ######## 6019 U1101508 ZIM STK1 3 ######## ########

Page 70sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 323545 dscfm 68 1 7 11.9 285 322625 dscfm 68 1 7 11.8 289 317107 dscfm 68 1 7.1 11.9 289 328565 dscfm 68 1 6.7 12.6 279 324723 dscfm 68 1 7.1 12.5 279 330121 dscfm 68 1 6.8 12.2 279 295591 dscfm 68 1 8.3 11.5 266 291834 dscfm 68 1 8.4 11.5 2.72 289686 dscfm 68 1 8.3 11.5 276 291829 dscfm 68 1 8.3 11.6 280 277136 dscfm 68 1 6.85 12.2 273 284284 dscfm 68 1 6.8 12.35 273 291587 dscfm 68 1 6.77 12.4 273 303297 dscfm 68 1 7 12.2 276 306867 dscfm 68 1 6.8 12.2 277 303735 dscfm 68 1 7.1 12 278 290645 dscfm 68 1 7.3 12.2 260 294442 dscfm 68 1 7 12.4 261 291577 dscfm 68 1 7.3 12.3 259 1051573 dscfm 68 1 7.1 13.2 300 1053363 dscfm 68 1 7.6 12.9 300 1049073 dscfm 68 1 7.1 13.3 300 290346 dscfm 68 1 5.7 13.2 273 286812 dscfm 68 1 5.5 13.8 277 285325 dscfm 68 1 5.9 13.3 279 277650 dscfm 68 1 6.7 12.1 271 233378 dscfm 68 1 6.4 12 274 237192 dscfm 68 1 6.1 12.5 274 236166 dscfm 68 1 6.8 12 265 236308 dscfm 68 1 6.5 12 270 261621 dscfm 68 1 6.1 12.7 277 266585 dscfm 68 1 6.4 12.9 278 278148 dscfm 68 1 6.6 12 276 277941 dscfm 68 1 6.8 12.2 2.76 287111 dscfm 68 1 6.4 12.6 279 285575 dscfm 68 1 6.5 12.8 280 286947 dscfm 68 1 6.4 12.9 278 287912 dscfm 68 1 7.3 12 280 285880 dscfm 68 1 7.1 11.9 281 283917 dscfm 68 1 7 12 285 274102 dscfm 68 1 6.5 13 281.2 276207 dscfm 68 1 7 13 281.2 270866 dscfm 68 1 7 13 290.8 338245 dscfm 68 1 7 11.7 300 332563 dscfm 68 1 7.2 11.85 300 339456 dscfm 68 1 7.2 11.85 300 380897 dscfm 68 1 7.4 12.3 248 382622 dscfm 68 1 7.6 12.1 251 388206 dscfm 68 1 7.3 12.1 251 371236 dscfm 68 1 8.4 11.4 274 367714 dscfm 68 1 8.1 11.7 275

Page 71sampling_runs

367111 dscfm 68 1 8.3 11.6 284 377065 dscfm 68 1 6 13.5 274 382384 dscfm 68 1 6 13.4 278 374840 dscfm 68 1 6.2 13.3 278 376726 dscfm 68 1 5 14.2 275 374949 dscfm 68 1 5.2 14 280 368842 dscfm 68 1 4.95 14.2 282 1001630 dscfm 68 1 7.2 13.1 300 1011134 dscfm 68 1 7.4 12.9 300 1039498 dscfm 68 1 7.1 13.1 300 499958 dscfm 68 1 9.51 10.56 259 506996 dscfm 68 1 9.51 10.65 258 508634 dscfm 68 1 9.47 10.52 257 419319 dscfm 68 1 7.21 11.98 272 420753 dscfm 68 1 7.22 11.99 275 415913 dscfm 68 1 7.21 11.98 275 993873 dscfm 68 1 4.48 14.9 300 1037128 dscfm 68 1 4.46 14.8 300 1050959 dscfm 68 1 4.64 14.73 300 1352359 dscfm 68 1 6.7 12.3 127 1342122 dscfm 68 1 6.6 12.2 127 1325935 dscfm 68 1 6.7 12.4 128 1323939 dscfm 68 1 6.8 12.4 128

1320574 dscfm 68 1 7 11.8 129 1318874 dscfm 68 1 7 12 129.6 1312930 dscfm 68 1 7 12 129.8 1313294 dscfm 68 1 7 11.8 129.8 1326505 dscfm 68 1 7.3 11.8 130.5 1353942 dscfm 68 1 6 13.2 131.7 1419322 dscfm 68 1 6.1 13.1 130 1412307 dscfm 68 1 6 13.2 131 1437986 dscfm 68 1 5.9 13.3 129 1425549 dscfm 68 1 7.8 11.3 130.8 1414677 dscfm 68 1 7.95 11.2 130.9 1427680 dscfm 68 1 7.85 11.25 130.8

1153150 dscfm 68 1 6.43 12.84 275 1166179 dscfm 68 1 6.33 12.89 275 1106467 dscfm 68 1 6.39 13.08 275 1365685 dscfm 68 1 6.4 13.05 129 1384643 dscfm 68 1 6.55 12.52 130 1373167 dscfm 68 1 5.9 12.72 129

1365685 dscfm 68 1 6.4 13.05 129

Page 72sampling_runs

1384643 dscfm 68 1 6.55 12.52 129.1 1373167 dscfm 68 1 5.9 12.72 129.2

2872796 dscfm 68 1 8.1 10.6 132 2959873 dscfm 68 1 8 10.7 132 3131910 dscfm 68 1 8.2 10.7 131 3102972 dscfm 68 1 7.5 12 130 3122558 dscfm 68 1 7.5 12.2 130 3094889 dscfm 68 1 7.5 12.6 131 3534759 dscfm 68 1 6.2 12.8 129 3540726 dscfm 68 1 6.9 12.1 130 3540620 dscfm 68 1 7 12 130

Page 73sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value 2.05 Method 5 2.05 Method 5 2.05 Method 5 2.002 Method 5 2.002 Method 5 2.002 Method 5 1.991 Method 5 1.991 Method 5 1.991 Method 5 1.991 Method 5 2.005 Method 5 2.005 Method 5 2.005 Method 5 1.983 Method 5 1.983 Method 5 1.983 Mehtod 5 2.029 Method 5 2.029 Method 5 2.029 Method 5 2.006 Method 5 2.006 Method 5 2.006 Method 5 2.032 Method 5 2.032 Method 5 2.032 Method 5 2.01 Method 5 2.01 Method 5 2.01 Method 5 1.999 Method 5 1.999 Method 5 1.999 Method 5 1.999 Method 5 2.008 Method 5 2.008 Method 5 2.008 Method 5 2.008 Method 5 2.008 Method 5 2.005 Method 5 2.005 Method 5 2.005 Method 5 2.023 Method 5 2.023 Method 5 2.023 Method 5 1.987 Method 5 1.987 Method 5 1.987 Method 5 2.016 Method 5 2.016 Method 5 2.106 Method 5 2.002 Method 5 2.002 Method 5

Page 74sampling_runs

2.002 Method 5 1.993 Method 5 1.993 Method 5 1.993 Method 5 2.03 Method 5 2.03 Method 5 2.03 Method 5 1.964 Method 5 1.964 Method 5 1.964 Method 5 2.018 Method 5 2.018 Method 5 2.018 Method 5 2.016 Method 5 2.016 Method 5 2.016 Method 5 1.996 Method 5 1.996 Method 5 1.996 Method 5 1.973 Method 5 1.973 Method 5 1.973 Method 5 1.973 Method 5

1.973 Method 5 1.959 Method 5 1.959 Method 5 1.956 Method 5 1.956 Method 5 1.947 Method 5 1.947 Method 5 1.947 Method 5 1.945 Method 5 1.946 Method 5 1.946 Method 5 1.946 Method 5

1.985 Method 5 1.985 Method 5 1.985 Method 5 1.978 Method 5 1.978 Method 5 1.978 Method 5

1.978 Method 6

Page 75sampling_runs

1.978 Method 6 1.978 Method 6

2.012 Method 5 2.012 Method 5 2.012 Method 5 1.964 Method 5 1.964 Method 5 1.964 Method 5 1.989 Method 5 1.989 Method 5 1.989 Method 5

Page 76sampling_runs

fuel_sulfur

Page 77sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_name conc conc_units conc_ND conc_MDL 2830 U4091305 WCB STK41 PM (Filterable) FALSE 2830 U4091305 WCB STK4 2 PM (Filterable) FALSE 2830 U4091305 WCB STK4 3 PM (Filterable) FALSE 6019 U1041205 ZIM STK1 1 PM (Filterable) FALSE 6019 U1041205 ZIM STK1 2 PM (Filterable) FALSE 6019 U1041205 ZIM STK1 3 PM (Filterable) FALSE 6019 U1 112007 ZIM STK1 1 PM (Filterable) FALSE 6019 U1 112007 ZIM STK1 2 PM (Filterable) FALSE 6019 U1 112007 ZIM STK1 3 PM (Filterable) FALSE 6019 U1072809 ZIM STK1 1 PM (Filterable) FALSE 6019 U1072809 ZIM STK1 2 PM (Filterable) FALSE 6019 U1072809 ZIM STK1 3 PM (Filterable) FALSE 6019 U1101508 ZIM STK1 1 Total Mercury (Hgt) 3.1 microgram per dry

standard cubic meter ( FALSE 6019 U1101508 ZIM STK1 2 Total Mercury (Hgt) 3.2 microgram per dry

standard cubic meter ( FALSE 6019 U1101508 ZIM STK1 3 Total Mercury (Hgt) 3.1 microgram per dry

standard cubic meter ( FALSE 2830 U5101105 WCB STK5,6 1 PM (Filterable) FALSE 2830 U5101105 WCB STK5,6 2 PM (Filterable) FALSE 2830 U5101105 WCB STK5,6 3 PM (Filterable) FALSE 2830 U1111605 WCB STK1 1 PM (Filterable) FALSE 2830 U1111605 WCB STK12 PM (Filterable) FALSE 2830 U1111605 WCB STK13 PM (Filterable) FALSE 2830 U6032806 WCB STK5,6 1 PM (Filterable) FALSE 2830 U6032806 WCB STK5,6 2 PM (Filterable) FALSE 2830 U6032806 WCB STK5,6 3 PM (Filterable) FALSE 2830 U2042506 WCB STK21 PM (Filterable) FALSE 2830 U2042506 WCB STK2 2 PM (Filterable) FALSE 2830 U2042506 WCB STK2 3 PM (Filterable) FALSE 2830 U2051806 WCB STK21 PM (Filterable) FALSE 2830 U2051806 WCB STK2 2 PM (Filterable) FALSE 2830 U2051806 WCB STK2 3 PM (Filterable) FALSE 2830 U2052406 WCB STK21 PM (Filterable) FALSE 2830 U2052406 WCB STK2 2 PM (Filterable) FALSE 2830 U2052406 WCB STK2 3 PM (Filterable) FALSE 2830 U2052406 WCB STK2 4 PM (Filterable) FALSE 2830 U2052506 WCB STK21 PM (Filterable) FALSE 2830 U2052506 WCB STK2 2 PM (Filterable) FALSE 2830 U2052506 WCB STK2 3 PM (Filterable) FALSE 2830 U2052506 WCB STK2 4 PM (Filterable) FALSE 2830 U2052506 WCB STK2 5 PM (Filterable) FALSE 2830 U2062806 WCB STK21 PM (Filterable) FALSE 2830 U2062806 WCB STK2 2 PM (Filterable) FALSE 2830 U2062806 WCB STK2 3 PM (Filterable) FALSE 2830 U1110706 WCB STK1 1 PM (Filterable) FALSE 2830 U1110706 WCB STK12 PM (Filterable) FALSE 2830 U1110706 WCB STK13 PM (Filterable) FALSE 2830 U2060607 WCB STK21 PM (Filterable) FALSE 2830 U2060607 WCB STK2 2 PM (Filterable) FALSE 2830 U2060607 WCB STK2 3 PM (Filterable) FALSE 2830 U1120407 WCB STK1 1 PM (Filterable) FALSE 2830 U1120407 WCB STK12 PM (Filterable) FALSE 2830 U1120407 WCB STK13 PM (Filterable) FALSE

Page 78sampling_run_pollutants1

2830 U3120507 WCBSTK3 1 PM (Filterable) FALSE 2830 U3120507 WCBSTK3 2 PM (Filterable) FALSE 2830 U3120507 WCBSTK3 3 PM (Filterable) FALSE 2830 U2021908 WCB STK21 PM (Filterable) FALSE 2830 U2021908 WCB STK2 2 PM (Filterable) FALSE 2830 U2021908 WCB STK2 3 PM (Filterable) FALSE 2830 U4022008 WCB STK41 PM (Filterable) FALSE 2830 U4022008 WCB STK4 2 PM (Filterable) FALSE 2830 U4022008 WCB STK4 3 PM (Filterable) FALSE 2830 U2022108 WCB STK21 PM (Filterable) FALSE 2830 U2022108 WCB STK2 2 PM (Filterable) FALSE 2830 U2022108 WCB STK2 3 PM (Filterable) FALSE 2830 U5033008 WCB STK5,6 1 PM (Filterable) FALSE 2830 U5033008 WCB STK5,6 2 PM (Filterable) FALSE 2830 U5033008 WCB STK5,6 3 PM (Filterable) FALSE 2830 U1121108 WCB STK1 1 PM (Filterable) FALSE 2830 U1121108 WCB STK12 PM (Filterable) FALSE 2830 U1121108 WCB STK13 PM (Filterable) FALSE 2830 U1120109 WCB STK1 1 PM (Filterable) FALSE 2830 U1120109 WCB STK12 PM (Filterable) FALSE 2830 U1120109 WCB STK13 PM (Filterable) FALSE 2830 U1120109 WCB STK14 PM (Filterable) FALSE 2832 U6030306 MFSU56STACK 1 PM (Filterable) FALSE 2832 U6030306 MFSU56STACK 2 PM (Filterable) FALSE 2832 U6030306 MFSU56STACK 3 PM (Filterable) FALSE 2832 U7032006 MFSU7STACK 1 PM (Filterable) FALSE 2832 U7032006 MFSU7STACK 2 PM (Filterable) FALSE 2832 U8082907FGDIN

U7FGDIN 1 Sulfur Dioxide (SO2) FALSE 2832 U8082907FGDIN

U7FGDIN 2 Sulfur Dioxide (SO2) FALSE 2832 U8082907FGDIN

U7FGDIN 3 Sulfur Dioxide (SO2) FALSE 2832 U8082907FGD

MFSU7STACK

1 Sulfur Dioxide (SO2) FALSE 2832 U8082907FGD

MFSU7STACK

2 Sulfur Dioxide (SO2) FALSE 2832 U8082907FGD

MFSU7STACK

3 Sulfur Dioxide (SO2) FALSE 2832 U8083007FGDIN

U8FGDIN 1 Sulfur Dioxide (SO2) FALSE 2832 U8083007FGDIN

U8FGDIN 2 Sulfur Dioxide (SO2) FALSE 2832 U8083007FGDIN

U8FGDIN 3 Sulfur Dioxide (SO2) FALSE 2832 U8083007FGD

MFSU8STACK

1 Sulfur Dioxide (SO2) FALSE 2832 U8083007FGD

MFSU8STACK

2 Sulfur Dioxide (SO2) FALSE 2832 U8083007FGD

MFSU8STACK

3 Sulfur Dioxide (SO2) FALSE 2832 U7052208FGDIN

U7FGDIN 1 Sulfur Dioxide (SO2) FALSE 2832 U7052208FGDIN

U7FGDIN 2 Sulfur Dioxide (SO2) FALSE 2832 U7052208FGDIN

U7FGDIN 3 Sulfur Dioxide (SO2) FALSE 2832 U7052208FGD

MFSU7STACK

1 Sulfur Dioxide (SO2) FALSE 2832 U7052208FGD

MFSU7STACK

2 Sulfur Dioxide (SO2) FALSE 2832 U7052208FGD

MFSU7STACK

3 Sulfur Dioxide (SO2) FALSE 2832 U7032006 MFSU7STACK 3 PM (Filterable) FALSE 2832 U8032106 MFSU8STACK 1 PM (Filterable) FALSE 2832 U8032106 MFSU8STACK 2 PM (Filterable) FALSE 2832 U8032106 MFSU8STACK 3 PM (Filterable) FALSE 2832 U8082907 MFSU8STACK 1 PM (Filterable) FALSE 2832 U8082907 MFSU8STACK 2 PM (Filterable) FALSE 2832 U8082907 MFSU8STACK 3 PM (Filterable) FALSE

Page 79sampling_run_pollutants1

2832 U6032708 MFSU56STACK 1 PM (Filterable) FALSE 2832 U6032708 MFSU56STACK 2 PM (Filterable) FALSE 2832 U6032708 MFSU56STACK 3 PM (Filterable) FALSE 2832 U7042908 MFSU7STACK 1 PM (Filterable) FALSE 2832 U7042908 MFSU7STACK 2 PM (Filterable) FALSE 2832 U7042908 MFSU7STACK 3 PM (Filterable) FALSE 2832 U7042908 MFSU7STACK 4 PM (Filterable) FALSE 2832 U7042908 MFSU7STACK 6 PM (Filterable) FALSE 2832 U7050108 MFSU7STACK 1 PM (Filterable) FALSE 2832 U7050108 MFSU7STACK 2 PM (Filterable) FALSE 2832 U7050108 MFSU7STACK 3 PM (Filterable) FALSE 2832 U7050108 MFSU7STACK 4 PM (Filterable) FALSE 2832 U7050808 MFSU7STACK 1 PM (Filterable) FALSE 2832 U7050808 MFSU7STACK 2 PM (Filterable) FALSE 2832 U7050808 MFSU7STACK 3 PM (Filterable) FALSE 2832 U7050808 MFSU7STACK 4 PM (Filterable) FALSE 2832 U7052008 MFSU7STACK 1 PM (Filterable) FALSE 2832 U7052008 MFSU7STACK 2 PM (Filterable) FALSE 2832 U7052008 MFSU7STACK 3 PM (Filterable) FALSE

Page 80sampling_run_pollutants1

emission_rate

emission_rate_units

emission_rate_ND

emission_rate_MDL

emission_factor

emission_factor_units

emission_factor_ND

emission_factor_MDL

run_pollutant_comment FALSE 0.043 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.044 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.055 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.019 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.015 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.025 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.019 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.017 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.026 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.005 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.005 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.005 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE 0.022 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.022 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.026 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.04 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.036 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.038 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.039 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.028 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.099 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.096 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.114 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.133 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.071 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.078 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.097 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.039 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.037 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.065 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.071 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.032 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.044 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.037 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.045 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.058 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.05 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.06 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.091 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.084 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.069 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.065 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.089 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.068 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.064 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.075 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.08 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.079 pound per million British Thermal Unit (lb/MMBtu) FALSE

Page 81sampling_run_pollutants1

FALSE 0.076 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.058 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.072 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.066 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.056 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.045 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.045 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.057 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.068 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.033 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.03 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.047 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.039 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.038 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.041 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.041 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.067 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.077 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.05 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.071 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.053 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.043 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.022 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.031 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.049 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.029 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.02 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 6.487 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 6.546 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 6.589 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.167 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.171 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.135 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 6.413 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 6.391 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 6.286 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.14 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.143 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.151 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 4.97 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 5.067 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 4.99 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.111 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.104 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.085 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.024 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.1 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.068 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.073 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.019 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.015 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.015 pound per million British Thermal Unit (lb/MMBtu) FALSE

Page 82sampling_run_pollutants1

FALSE 0.015 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.032 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.026 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.035 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.053 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.047 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.05 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.011 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.02 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.009 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.011 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.01 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.012 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.013 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.012 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.02 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.008 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.023 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.019 pound per million British Thermal Unit (lb/MMBtu) FALSE

Page 83sampling_run_pollutants1

run_pollutant_comment

Page 84sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL

Page 85sampling_run_fuel

fuel_conc_MDL

Page 86