Index | Site       Map | FAQ | Facility       Info | Reading       Rm | New | Help | Glossary | Contact UsProtecting People and the EnvironmentUNITED STATES NUCLEAR REGULATORY COMMISSION -   About NRC    - The     Commission 
  - Statutory Authority 
  - Strategic Plan 
  - Budget &      Performance 
  - Organization & Functions 
  - Locations 
  - History 
  - Values 
  - Policymaking 
  - Radiation Protection 
  - Fire Protection 
  - How We Regulate 
  - Grants 
  - Civil Rights 
  - 
- NuclearReactors    - Operating Reactor Locations 
  - Reactor Quick Links 
  - Power Reactors 
  - Research and Test     Reactors 
  - Operating Reactors 
  - Operator Licensing 
  - New Reactors 
  - Operator     Licensing for New Reactors 
  - Reactor Safety Research 
  - Advisory Comm (ACRS) 
  - Decommissioning     of Nuclear Facilities 
  - 
- NuclearMaterials    - Fuel Cycle Facility Locations 
  - Uranium     Recovery Locations 
  - Materials Quick Links 
  - Special Nuclear Material 
  - Source Material 
  - Byproduct Material 
  - Med, Academic & Ind Uses 
  - Source Materials Facilities 
  - Uranium Recovery 
  - Fuel Cycle Facilities 
  - Materials     Transportation 
  - Materials Research 
  - Advisory Comm (ACMUI) 
  - Decommissioning     of Nuclear Facilities 
  - Materials     Environmental Reviews 
  - 
- RadioactiveWaste    - Waste Quick Links 
  - Low-Level Waste 
  - Waste Incidental to     Reprocessing 
  - Incidental Waste Criteria 
  - High-Level Waste 
  - Uranium Mill Tailings 
  - LLW Disposal 
  - HLW Disposal 
  - Spent Fuel Storage 
  - Spent Fuel Transport 
  - Waste Research 
  - 
- NuclearSecurity    - Security     Spotlight 
  - NRC     Responsibilities 
  - Domestic Safeguards 
  - Radioactive Material Security 
  - Facility Protection 
  - Nuclear Material Control 
  - International Safeguards 
  - Information Security 
  - Emergency     Preparedness 
  - &; 
- Public Meetings&   Involvement    - Public Meeting Schedule 
  - Commission     Schedule 
  - Conferences & Symposia 
  - Documents for Comment 
  - Brochures & Fact Sheets 
  - Involving Stakeholders 
  - Info Quality Guidelines 
  - Rulemaking Process 
  - Licensing 
  - Enforcement 
  - Hearing Process 
  - Hearing Applications 
  - 

Home       > Electronic Reading       Room       > Document       Collections       > General       Communications       > Information       Notices       > 2001       > IN 2001-19

UNITED STATESNUCLEAR REGULATORY COMMISSIONOFFICE OF NUCLEAR REACTOR REGULATIONWASHINGTON, D.C. 20555-0001

December 17, 2001

Information Notice No. 2001-19: IMPROPER MAINTENANCE AND REASSEMBLY OF AUTOMATIC OIL BUBBLERS
- Addressees 
- Purpose 
- Background 
- Description   of Circumstances 
- Discussion 
Addressees
All holders of operating licenses for nuclear power reactors, except those who have permanently ceased operations and have certified that fuel has been permanently removed from the reactor vessel.
Purpose
The U.S. Nuclear Regulatory Commission (NRC) is issuing this information notice to alert addressees to recent problems resulting from improper maintenance and reassembly of automatic oil bubblers. The NRC expects all recipients to review the information for applicability to their facilities and consider actions, as appropriate, to avoid potential problems. However, the recommendations contained in this information notice do not constitute NRC requirements; therefore, this information notice does not require any specific actions or written response.
Background
Recent problems raised concerns regarding improper maintenance and reassembly of automatic oil bubblers. These oil bubblers are used to maintain the oil level in the pump bearing housing of safety-related equipment. Blockage of oil flow from the bubbler, along with periodic loss of oil through equipment operation and routine oil sampling, could deplete the oil level to the point where severe equipment damage could result. This issue was first identified at Millstone Nuclear Power Station Unit 2, in August 2000, then at Joseph M. Farley Nuclear Plant, Unit 1 in January 2001, and later at Seabrook in June 2001. The degraded oil bubblers at Seabrook involved both emergency feedwater pumps. 

The concern arises when the oil feed pipe entering the bottom of the oil bubbler extends beyond the threaded fitting (protruding too far into the housing), thereby allowing the pipe to make contact with the level adjuster (flat disc) mechanism. The contact between the oil feed pipe and the disc could block the essential oil flow from the bubbler to the bearing reservoir. (See attachment 2.)
Discussion
Within the past year, two power plants have experienced a situation that resulted in the malfunction of the automatic oiler feature for the bearings on safety-related equipment. The Trico Opto-Matic oiler that malfunctioned is commonly used in many applications in power plants; therefore, the potential exists for similar malfunctions to affect other plant components.

Plant personnel typically use the oil level in the glass reservoir as a visual indication that an adequate supply of oil is available to replenish the reservoir of the component on which it is installed. The oil for the equipment reservoir is supplied via a 1/4 inch threaded pipe that can be connected through either the side of the lower housing or from the bottom (Attachment 2, figure a.) The problem arises when the supply piping (1/4 inch, 18-NPT, threaded connecting nipple) is threaded into the oiler base so far that the pipe begins to protrude into the lower base of the oiler (Attachment 2, figure b.) In both plants that experienced this problem, the oil bubbler involved was an early Trico design from the 1970s, which contained a "flat-based" spider assembly that controlled the flow of oil from the bubbler to the equipment being supplied. Trico has since changed the design of the oil bubbler spider assembly to incorporate a concave-shaped spider base (Attachment 2, figure c.) This design minimizes the potential for the connecting pipe to make contact with the spider base by extending a total of inch above the oiler base supply port. As a result, this design greatly minimizes the potential for a flow restriction to develop between the bubbler reservoir and the equipment bearing housing. The potential for problems exists only when the oiler feed supply line is connected to the bottom of the oiler base with a flat-based spider assembly. 

The EPRI's Nuclear Maintenance Application Center (NMAC) and the NMAC Pump Users Group recommend that licensees take the following actions to ensure that this condition does not affect equipment performance and availability:
- Verify existing oil levels using redundant means, such as a dipstick with   secured equipment or visual inspection through the equipment oil reservoir   sample/inspection ports while the pump is running.     
- As soon as possible, determine if the connecting fitting protrudes into   the base of the Trico oil bubbler housing, by removing the bubbler bulb and   spider assembly and feeling the bottom of the bubbler base for the protruding   1/4 inch fitting.     
- At the earliest opportunity, install oil bubblers with the concave-style   spider assembly to avoid the possibility of an improperly functioning oiler or   oil level indication.     
- Change the applicable procedures so that oil change/sampling, and   post-maintenance test procedures fill the oil reservoir using a consistent   technique as recommended. 

Additional detailed information can be found in NRC Inspection Report 50-443/01-07, "SEABROOK STATION - NRC INSPECTION REPORT," dated July 27, 2001, Accession 

This information notice does not require any specific action or written response. If you have any questions about the information in this notice, please contact the technical contact listed below or the appropriate project manager in the NRC's Office of Nuclear Reactor Regulation (NRR).

This information notice requires no specific action or written response. If you have any questions about the information in this notice, please contact one of the technical contacts listed below or the appropriate Office of Nuclear Reactor Regulation (NRR) project manager. 
/RAEugene V. Imbro, Acting       ChiefOperational Experience    and Non-Power       Reactors BranchDivision of Regulatory Improvement ProgramsOffice       of Nuclear Reactor RegulationTechnical contacts:Omid Tabatabai, NRR(301) 415-3738E-mail:       oty@nrc.govJavier Brand, Region 1(301) 474-3589E-mail:   jmb3@nrc.gov
Attachment: Figure 2
- List of Recently Issued NRC Information Notices   
- Trico   Opto-Matic Oil Bubbler figures 
(ADAMS Accession Number ML013250229)