Index | Site       Map | FAQ | Facility       Info | Reading       Rm | New | Help | Glossary | Contact UsProtecting People and the EnvironmentUNITED STATES NUCLEAR REGULATORY COMMISSION -   About NRC    - The     Commission 
  - Statutory Authority 
  - Strategic Plan 
  - Budget &      Performance 
  - Organization & Functions 
  - Locations 
  - History 
  - Values 
  - Policymaking 
  - Radiation Protection 
  - Fire Protection 
  - How We Regulate 
  - Grants 
  - Civil Rights 
  - 
- NuclearReactors    - Operating Reactor Locations 
  - Reactor Quick Links 
  - Power Reactors 
  - Research and Test     Reactors 
  - Operating Reactors 
  - Operator Licensing 
  - New Reactors 
  - Operator     Licensing for New Reactors 
  - Reactor Safety Research 
  - Advisory Comm (ACRS) 
  - Decommissioning     of Nuclear Facilities 
  - 
- NuclearMaterials    - Fuel Cycle Facility Locations 
  - Uranium     Recovery Locations 
  - Materials Quick Links 
  - Special Nuclear Material 
  - Source Material 
  - Byproduct Material 
  - Med, Academic & Ind Uses 
  - Source Materials Facilities 
  - Uranium Recovery 
  - Fuel Cycle Facilities 
  - Materials     Transportation 
  - Materials Research 
  - Advisory Comm (ACMUI) 
  - Decommissioning     of Nuclear Facilities 
  - Materials     Environmental Reviews 
  - 
- RadioactiveWaste    - Waste Quick Links 
  - Low-Level Waste 
  - Waste Incidental to     Reprocessing 
  - Incidental Waste Criteria 
  - High-Level Waste 
  - Uranium Mill Tailings 
  - LLW Disposal 
  - HLW Disposal 
  - Spent Fuel Storage 
  - Spent Fuel Transport 
  - Waste Research 
  - 
- NuclearSecurity    - Security     Spotlight 
  - NRC     Responsibilities 
  - Domestic Safeguards 
  - Radioactive Material Security 
  - Facility Protection 
  - Nuclear Material Control 
  - International Safeguards 
  - Information Security 
  - Emergency     Preparedness 
  - &; 
- Public Meetings&   Involvement    - Public Meeting Schedule 
  - Commission     Schedule 
  - Conferences & Symposia 
  - Documents for Comment 
  - Brochures & Fact Sheets 
  - Involving Stakeholders 
  - Info Quality Guidelines 
  - Rulemaking Process 
  - Licensing 
  - Enforcement 
  - Hearing Process 
  - Hearing Applications 
  - 

Home       > Electronic Reading       Room       > Document       Collections       > General       Communications       > Information       Notices       > 2002       > IN 2002-06

UNITED STATESNUCLEAR REGULATORY COMMISSIONOFFICE OF NUCLEAR REACTOR REGULATIONWASHINGTON, D.C. 20555-0001

January 18, 2002

NRC INFORMATION NOTICE 2002-06: DESIGN VULNERABILITY IN BWR REACTOR VESSEL LEVEL INSTRUMENTATION BACKFILL MODIFICATION
- Addressees 
- Purpose 
- Description   of Circumstances 
- Discussion 
Addressees
All holders of operating licenses or construction permits for boiling water reactors (BWRs).
Purpose
The U.S. Nuclear Regulatory Commission (NRC) is issuing this information notice to alert addressees to a potential design vulnerability in a hardware modification to the reactor vessel water level instrumentation system. It is expected that recipients will review the information for applicability to their facilities and consider actions, as appropriate, to avoid similar problems. However, suggestions contained in this information notice are not NRC requirements; therefore, no specific action or written response is required.
Background
NRC Bulletin (NRCB) 93-03, "Resolution of Issues Related to Reactor Vessel Water Level Instrumentation in BWRs," issued on May 28, 1993, requested that licensees implement hardware modifications necessary to ensure the level instrumentation system design is of high functional reliability for long-term operation. In response to this bulletin, all BWR licensees with the exception of Big Rock Point, which does not use cold-reference-leg instrumentation, have either implemented or committed to implement modifications. The majority of these licensees have decided to install a reference leg backfill system to supply a continuous flow of water from the control rod drive (CRD) hydraulic system through the reference legs. The back-fill system precludes migration of dissolved noncondensible gases down the legs. In August 2001, a design vulnerability in this backfill modification was found at the Pilgrim Nuclear Power Station.
Description of Circumstances
It was discovered that, under certain conditions, the safety-related reactor vessel water level indicators that provide certain safety-related initiation signals could give nonconservative water level readings. During a reactor trip at Pilgrim, both trains of the emergency core cooling system (ECCS) reactor water level instruments indicated higher than actual levels. These instrument inaccuracies were noted after operator actions were taken to isolate the CRD system charging water header supply valve, CRD 301-25, to insert a control rod that had not settled at position 00. Closure of the charging water header isolates the ECCS level indicator reference-leg backfill system (see Attachment 1). The erroneous readings were attributed to the reference legs draining back through the reference-leg keepfill system to the CRD hydraulic control units (HCUs). With the CRD charging header valve shut, the reactor scram reset, and reactor pressure rising, the reference legs drained back to the HCUs. This occurs when the CRD system pump is secured or the charging header isolation valve is closed, the source of the reference-leg keepfill system, is at a slightly lower pressure than the reactor so that the differential pressure across the keepfill system check valve is not sufficient to fully seat the check valves. The draining of the reference legs results in a transient false reference-leg indication until the check valves seat and the reference legs refill via the condensate pots or flow is reestablished through the CRD reference leg backfill system. Pilgrim concluded that this phenomenon can occur with either the isolation of the reference leg backfill system or possibly with the loss of the running CRD pump.

During the reactor scam at Pilgrim, this event resulted in both the wide-range vessel level instruments indicating higher than actual water level with the A train reaching a maximum deviation of 26 inches and the B train reaching a maximum of 11 inches. These erroneous high readings occurred for approximately 30 minutes. During this time, the automatic emergency core cooling system initiation function would not have occurred on low-low water level as designed. This false reading is due to the relative locations of the reactor vessel instrument nozzles and the differential pressure corresponding to the ECCS initiation setpoint.

Related Generic Communications:
NRC Information Notice 93-89"Potential Problems With BWR Level Instrumentation Backfill       Modifications," November 26, 1993NRC Information Notice 92-54"Level Instrumentation Inaccuracies Caused by Rapid Depressurization,"       July 24, 1992Generic Letter 92-04"Resolution of the Issues Related to Reactor Vessel Water Level       Instrumentation in BWRs Pursuant to 10 CFR 50.54(f)," August 19, 1992NRC Information Notice 93-27"Level Instrumentation Inaccuracies Observed During Normal Plant       Depressurization," April 8, 1993NRC Bulletin 93-03"Resolution of Issues Related to Reactor Vessel Water Level       Instrumentation in BWRs," May 28, 1993
This information notice requires no specific action or written response. If you have any questions regarding the information notice, please contact the technical contacts listed below or the appropriate Office of Nuclear Reactor Regulation (NRR) project manager.
/RA/       
William D. Beckner, Program DirectorOperating Reactor Improvements       ProgramDivision of Regulatory Improvement ProgramsOffice of       Nuclear Reactor Regulation
Technical contacts:R. Arrighi, Region I508-747-0565E-mail:       rja1@nrc.govThomas Koshy, NRR301-415-1176E-mail: txk@nrc.gov
Attachments:
- Sketch   of Backfill Modification   
- List of Recently Issued NRC Information Notices 
(ADAMS Accession Number ML013470481)