Index | Site       Map | FAQ | Facility       Info | Reading       Rm | New | Help | Glossary | Contact UsProtecting People and the EnvironmentUNITED STATES NUCLEAR REGULATORY COMMISSION -   About NRC    - The     Commission 
  - Statutory Authority 
  - Strategic Plan 
  - Budget &      Performance 
  - Organization & Functions 
  - Locations 
  - History 
  - Values 
  - Policymaking 
  - Radiation Protection 
  - Fire Protection 
  - How We Regulate 
  - Grants 
  - Civil Rights 
  - 
- NuclearReactors    - Operating Reactor Locations 
  - Reactor Quick Links 
  - Power Reactors 
  - Research and Test     Reactors 
  - Operating Reactors 
  - Operator Licensing 
  - New Reactors 
  - Operator     Licensing for New Reactors 
  - Reactor Safety Research 
  - Advisory Comm (ACRS) 
  - Decommissioning     of Nuclear Facilities 
  - 
- NuclearMaterials    - Fuel Cycle Facility Locations 
  - Uranium     Recovery Locations 
  - Materials Quick Links 
  - Special Nuclear Material 
  - Source Material 
  - Byproduct Material 
  - Med, Academic & Ind Uses 
  - Source Materials Facilities 
  - Uranium Recovery 
  - Fuel Cycle Facilities 
  - Materials     Transportation 
  - Materials Research 
  - Advisory Comm (ACMUI) 
  - Decommissioning     of Nuclear Facilities 
  - Materials     Environmental Reviews 
  - 
- RadioactiveWaste    - Waste Quick Links 
  - Low-Level Waste 
  - Waste Incidental to     Reprocessing 
  - Incidental Waste Criteria 
  - High-Level Waste 
  - Uranium Mill Tailings 
  - LLW Disposal 
  - HLW Disposal 
  - Spent Fuel Storage 
  - Spent Fuel Transport 
  - Waste Research 
  - 
- NuclearSecurity    - Security     Spotlight 
  - NRC     Responsibilities 
  - Domestic Safeguards 
  - Radioactive Material Security 
  - Facility Protection 
  - Nuclear Material Control 
  - International Safeguards 
  - Information Security 
  - Emergency     Preparedness 
  - &; 
- Public Meetings&   Involvement    - Public Meeting Schedule 
  - Commission     Schedule 
  - Conferences & Symposia 
  - Documents for Comment 
  - Brochures & Fact Sheets 
  - Involving Stakeholders 
  - Info Quality Guidelines 
  - Rulemaking Process 
  - Licensing 
  - Enforcement 
  - Hearing Process 
  - Hearing Applications 
  - 

Home       > Electronic Reading       Room       > Document       Collections       > General       Communications       > Information       Notices       > 2002       > IN 2002-10

UNITED STATESNUCLEAR REGULATORY COMMISSIONOFFICE OF NUCLEAR REACTOR REGULATIONWASHINGTON, D.C. 20555-0001

March 7, 2002

NRC INFORMATION NOTICE 2002-10: NONCONSERVATIVE WATER LEVEL SETPOINTS ON STEAM GENERATORS
- Addressees 
- Purpose 
- Description   of Circumstances 
Addressees
All holders of operating licenses for nuclear power reactors, except those who have permanently ceased operations and have certified that fuel has been permanently removed from the reactor.
Purpose
The U.S. Nuclear Regulatory Commission (NRC) is issuing this information notice to alert addressees to the potential for nonconservative setpoints for steam generator water level. The NRC anticipates that recipients will review this information for applicability to their facilities and consider taking appropriate actions. However, the suggestions contained in this information notice do not constitute NRC requirements and, therefore, no specific action or written response is required.
Description of Circumstances
Diablo Canyon Power Plant reported that the narrow-range steam generator water level instrumentation did not respond as expected to initiate an automatic reactor trip and emergency feedwater actuation on low-low water level in the steam generator during a plant trip of Unit 2 on February 9, 2002. 

The low-low setpoint (7.2 percent) for the narrow-range steam generator water level provides a signal to automatically trip the reactor and actuate the emergency feedwater system. On February 9, 2002, the main feedwater regulating valve failed closed, resulting in a rapid decrease in the steam generator water level. Operators manually tripped the reactor as the level decreased to approximately 7.5 percent on the narrow-range, with the wide-range indicating approximately 16 percent. This manual trip of the reactor by the operators occurred within approximately 1 minute after the main feedwater regulating valve closed. Following the manual trip, the steam generator wide-range water level indication continued to decrease to a low of 10 percent when the steam generator water level began to stabilize. The level then trended upward as emergency feedwater began to refill the steam generator. On the basis of the post-trip review and conversations with Westinghouse, the manufacturer of the steam generator, Pacific Gas and Electric concluded that the steam generator water level actually fell below the 7.2 percent low-low steam generator water level setpoint before the operator manually tripped the reactor. In response, the operators declared all narrow-range steam generator water level low-low channels inoperable and entered Plant Technical Specification

Action 3.0.3. Under that action, the operators reduced the power level of both Units 1 and Unit 2 to approximately 60 percent, where Westinghouse had indicated that the condition would no longer result in a non-conservative setpoint.

This event provides insight into setpoint errors in the steam generator water level which could delay the expected automatic reactor trip and emergency feedwater actuation. The licensee reported that Westinghouse attributes this water level discrepancy to previously unaccounted for differential pressure created by steam flow past the mid-deck plate in the moisture separator section of the steam generator. Westinghouse further indicated that this differential pressure phenomenon will cause the steam generator narrow-range to read higher than the actual water level at steam flows when the reactor is operating at a power level greater than 60 percent for Diablo Canyon. Thus, all steam generator water level instrumentation associated with this reference leg could be nonconservative during certain transients because of this differential pressure phenomenon. Diablo Canyon has since recalibrated the low-low water level setpoints for the steam generator with the additional margin to account for this newly identified error. The licensee completed this instrument recalibration before increasing the plant's power level above 60 percent.

This information notice does not require any specific action or written response. If you have any questions about the information in this notice, please contact the technical contact listed below or the appropriate project manager from the NRC's Office of Nuclear Reactor Regulation. 
/RA/       
William D. Beckner, Program DirectorOperating Reactor Improvements       ProgramDivision of Regulatory Improvement ProgramsOffice of       Nuclear Reactor Regulation
Technical contacts:Jerry Dozier, NRR(301)-415-1014E-mail:     jxd@nrc.govAttachment: List of Recently Issued NRC Information Notices (ADAMS Accession Number ML020660177)