Technical Report

NREL/TP-500-47496

July 2010

Wind Turbine Safety and 

Function Test Report for the 

Mariah Windspire Wind Turbine

Arlinda Huskey, Amy Bowen, and Dave Jager
National Renewable Energy Laboratory

1617 Cole Boulevard, Golden, Colorado 80401-3393

303-275-3000 • www.nrel.gov

NREL is a national laboratory of the U.S. Department of Energy

Office of Energy Efficiency and Renewable Energy

Operated by the Alliance for Sustainable Energy, LLC

Contract No. DE-AC36-08-GO28308

Technical Report

NREL/TP-500-47496

July 2010

Wind Turbine Safety and 

Function Test Report for the 

Mariah Windspire Wind Turbine

Arlinda Huskey, Amy Bowen, and Dave Jager

Prepared under Task No. WE10.2211
NOTICE

This report was prepared as an account of work sponsored by an agency of the United States government. 

Neither the United States government nor any agency thereof, nor any of their employees, makes any 

warranty, express or implied, or assumes any legal liability or responsibility for the accuracy, completeness, or 

usefulness of any information, apparatus, product, or process disclosed, or represents that its use would not 

infringe privately owned rights. Reference herein to any specific commercial product, process, or service by 

trade name, trademark, manufacturer, or otherwise does not necessarily constitute or imply its endorsement, 

recommendation, or favoring by the United States government or any agency thereof. The views and 

opinions of authors expressed herein do not necessarily state or reflect those of the United States 

government or any agency thereof.

Available electronically at http://www.osti.gov/bridge

Available for a processing fee to U.S. Department of Energy

and its contractors, in paper, from:

U.S. Department of Energy

Office of Scientific and Technical Information

P.O. Box 62

Oak Ridge, TN 37831-0062

phone: 865.576.8401

fax: 865.576.5728

email: mailto:reports@adonis.osti.gov

Available for sale to the public, in paper, from:

U.S. Department of Commerce

National Technical Information Service

5285 Port Royal Road

Springfield, VA 22161

phone: 800.553.6847

fax: 703.605.6900

email: orders@ntis.fedworld.gov

online ordering: http://www.ntis.gov/ordering.htm

Printed on paper containing at least 50% wastepaper, including 20% postconsumer waste
i

Notice

This report was prepared by the National Renewable Energy Laboratory (NREL), operated for 

the United States Department of Energy (DOE) by the Alliance for Sustainable Energy, LLC 

(Alliance), as an account of work sponsored by the United States government. The test results 

documented in this report define the characteristics of the test article as configured and under 

the conditions tested.

This report is provided “as is” and neither the government, Alliance, NREL, nor any of their 

employees makes any warranty, express or implied, including the warranties of merchantability 

and fitness for a particular purpose, or assumes any legal liability or responsibility for the 

accuracy, completeness, or usefulness of any such information disclosed in the report, or of any 

apparatus, product, or process disclosed, or represents that its use would not infringe privately 

owned rights.

Neither Alliance nor the United States government shall be liable for special, consequential, or 

incidental damages. Reference herein to any specific commercial product, process, or service 

by trade name, trademark, manufacturer, or otherwise does not necessarily constitute or imply 

its endorsement, recommendation, or favoring by the United States government or any agency 

thereof. The views and opinions of the authors expressed herein do not necessarily state or 

reflect those of the United States government or any agency thereof or Alliance.

NREL is a DOE Laboratory and, as an adjunct of the United States government, cannot certify 

wind turbines. The information in this report is limited to NREL’s knowledge and understanding 

as of this date.

NREL is accredited by the American Association for Laboratory Accreditation (A2LA) and the 

results shown in this test report have been determined in accordance with the NREL’s terms of 

accreditation unless stated otherwise in the report.

This report shall not be reproduced, except in full, without the written approval of Alliance or 

successor operator of NREL.

Approval By:___________________________________________________________

 Arlinda Huskey, NREL Test Engineer Date

Approval By:___________________________________________________________

 Jeroen van Dam, NREL Test Engineer Date
ii

List of Acronyms

AWG American Wire Gauge

DOE United States Department of Energy

NREL National Renewable Energy Laboratory

NWTC National Wind Technology Center

SWT small wind turbine
iii

Table of Contents

List of Acronyms........................................................................................................... ii

List of Figures .............................................................................................................. iv

List of Tables ................................................................................................................ iv

1 Background............................................................................................................. 1

2 Test Objective ......................................................................................................... 1

3 Description of Test Turbine and Setup................................................................. 1

4 Instrumentation....................................................................................................... 4

5 Procedure................................................................................................................ 4

5.1 Control and Protection System Functions.................................................................................................4

5.2 Personnel Safety Provisions .......................................................................................................................5

5.3 Dynamic Behavior ........................................................................................................................................6

6 Results..................................................................................................................... 6

6.1 Control and Protection System Functions.................................................................................................6

6.2 Personnel Safety Provisions .......................................................................................................................8

6.3 Dynamic Behavior ......................................................................................................................................10

7 Deviations and Exceptions .................................................................................. 15

7.1 Deviations from the Standard ...................................................................................................................15

7.2 Exceptions to the NWTC Quality Assurance System............................................................................15

Appendix A. Instrument Calibration Sheets ............................................................. 16
iv

List of Figures

Figure 1. Windspire wind turbine at the NWTC test site ...............................................................3

Figure 2. Electrical one-line drawing.............................................................................................3

Figure 3. Power response to wind speed....................................................................................11

Figure 4. Rotor-speed response to wind speed ..........................................................................11

Figure 5. Normal start-up, wind speeds greater than cut-in........................................................12

Figure 6. Normal start-up after maintenance ..............................................................................12

Figure 7. Normal shut down, winds decreasing below cut in ......................................................13

Figure 8. Normal shut down, maintenance at design wind speed or greater..............................13

Figure 9. Emergency stop at wind speeds less than the design wind speed..............................14

Figure 10. Emergency stop at design wind speed or greater .....................................................14

List of Tables

Table 1. Test Turbine Configuration .............................................................................................2

Table 2. Equipment List for Safety and Function Test ..................................................................4
1

1 Background

This test was conducted as part of the U.S. Department of Energy’s (DOE) Independent 

Testing project. This project was established to help reduce the barriers to wind energy 

expansion by providing independent testing results for small wind turbines (SWT). In total, 

five turbines were tested at the National Wind Technology Center (NWTC) as a part of this 

project. Safety and function testing is one of up to five tests performed on the turbines, 

including power performance, duration, noise, and power-quality tests. NWTC testing results 

provide manufacturers with reports that may be used to meet part of small wind turbine 

certification requirements.

The test equipment includes a Windspire wind turbine mounted on a monopole tower. L&E 

Machine manufactured the turbine in the United States. The inverter was manufactured 

separately by Technology Driven Products in the United States. The system was installed by 

the NWTC site operations group with guidance and assistance from Mariah Power.

During this test, two configurations were tested on the same turbine. In the first configuration, 

the turbine inverter was optimized for power production. In the second configuration, the 

turbine inverter was set for standard power production. In both configurations, the inverter 

experienced failures. Tests from both of these configurations are included in the report, 

though each test was not performed on both configurations of the turbine. Testing on the 

Windspire was terminated before all of the planned safety and function tests could be 

completed.

2 Test Objective

The objective of this test was to:

• Verify whether the test turbine displays the behavior predicted in the design;

• Determine whether provisions relating to personnel safety are properly implemented; 

and

• Characterize the dynamic behavior of the wind turbine at rated wind speed and greater

speeds.

The National Renewable Energy Laboratory (NREL) does not limit safety and function tests 

to features described in the wind turbine documentation, and NREL also inspects—possibly 

tests—and reports on features that are required by IEC 61400-2 and that might not be 

described in the wind turbine documentation. NREL conducted this test in accordance with 

Section 9.6 of the IEC standard, “Wind Turbines—Part 2: Design Requirements for Small 

Wind Turbines,” IEC 61400-2, second edition, 2006-03.

3 Description of Test Turbine and Setup

The test turbine was a Mariah Power Windspire wind turbine. This turbine is a vertical axis, 

three-bladed, variable-speed, turbine with a rated power of 1-kW. Figure 1 shows the test 
2

turbine installed at the NWTC. Table 1 provides the key descriptive information of the test 

turbine.

Table 1. Test Turbine Configuration

Turbine manufacturer name

and address

Mariah Power

748 S. Meadows Pkwy. A-9, 

#329

Reno, NV 89521

Model name Windspire

Serial number 800021

Revision number 1P

Production date 2008

Design nominal voltage at terminals (VAC) 120

Maximum current at terminals (A) 20

Design frequency at terminals (Hz) 60

Small wind turbine (SWT) class IV

Design 50-year extreme wind speed, Ve50 (m/s) 42

Equivalent Rotor diameter (m) 3.08

Hub height (vertical center of rotor) (m) 6.10

Tower type Tubular

Rated electrical power (kW) 1

Rated wind speed (m/s) (slowest wind speed 

at which turbine produces rated power)

11.0

Rated rotor speed (rpm) (slowest rotor speed 

at which turbine produces rated power)

180

Rotor speed range (rpm) 0 – 500

Fixed or variable pitch Fixed

Number of blades 3

Blade pitch angle (deg) 3

Blade make, type, serial number Mariah Power, Airfoil, NA

Description of control system (device & software Windspire 1.2G

The Windspire wind turbine was installed at site 3.3C at the NWTC, which is located 8 miles 

south of Boulder, Colorado. The site’s terrain primarily is flat with short vegetation. The test 

site has prevailing wind bearing 292 degrees relative to true north. For measurements 

requiring highly accurate wind-speed data, NREL used data obtained when the wind direction 

was between 132 degrees true to 323 degrees true. In this measurement sector—which was 

established in accordance with IEC 61400-12-1—the influence of terrain and obstructions on 

the anemometer and turbine is slight.

Figure 2 shows the general electrical arrangement. The wire run from the base of the tower to 

the data shed is approximately 54 meters of #12-2 American Wire Gauge (AWG) wire. Inside 

the data shed, on the turbine side of the transformer, the wire run is connected to a disconnect 

switch and a dedicated breaker in a breaker panel. 
3

Figure 1. Windspire wind turbine at the NWTC test site

Disconnect

Switch

Test Shed

Breaker Panel

120/240 VAC

20 Amp

To data 

acquisition

kWh

Meter

#12-2 with 

ground

To NREL grid

RPM, Status 

Signals

Met Tower 

J-Box

Power

Transducer Box

Instrumentation 

cable

Figure 2. Electrical drawing
4

4 Instrumentation

The following parameters were measured in this test: wind speed, electrical power, rotor 

speed, turbine status, and grid voltage. The rotor speed was calculated by measuring the 

frequency of an optically isolated signal from the turbine. The turbine does not produce a 

detectable rotor speed signal at lower rotor speeds. An indication of turbine status was 

obtained by measuring the voltage of a signal from the turbine that indicated if the turbine’s 

brake was on. The instruments used for these measurements are listed in Table 2. The 

calibration sheets for the instruments used for this safety and function test are included in 

Appendix A.

Table 2. Equipment List for Safety and Function Test

Instrument Make, Model

Serial 

Number Calibration Due Date

Power 

transducer

Second Wind, Phaser 

5FM-4A20 02061 February 8, 2009

Voltage

transducer

Ohio Semitronics, VT7-

010E-11 08010700 Calibrated with power transducer

Primary 

anemometer Thies, First Class 0707894 February 27, 2009

Compact DAQ w/LabView

Data acquisition 

system

cDAQ backplane

NI 9229

NI 9217

NI 9205

12E4D23

12B6DD2

12BD192

12E9C3E

June 28, 2008

July 6, 2008

October 8, 2008

Modules post-test calibrated on

May 6, 2009 and found in 

compliance

5 Procedure

Safety and function testing can involve some risk to personnel and to equipment. By incorporating appropriate controls into testing procedures, NREL endeavors to accomplish its tasks 

with minimal risk. This test report documents these controls in areas where they might have 

influenced the results obtained.

5.1 Control and Protection System Functions

The first part of the test procedure is assessing the control and protection system functions.

The planned control and protection system tests are listed below, though not all were 

completed before testing was terminated. The turbine’s response is observed for each major 
5

response category (start-up, normal shutdown, emergency shutdown) in the list below. In 

circumstances in which faults or other actions cause one of these major responses, NREL staff 

simulates the appropriate input and verifies that the control and protection system 

appropriately sensed the condition and provided an indication of the appropriate response.

This procedure, for example, enables rotor overspeed functions to be checked without 

exposing the turbine to multiple potentially damaging stops. In the list below, these items are 

designated by the term “behavior.”

1. Power control

2. Rotor-speed control

3. Start-up

a. Normal operation—wind speed greater than cut-in

b. After maintenance or fault clearance at design wind speed or greater

4. Normal shutdown under

a. Normal operation—wind speed decreasing to less than cut-in

b. Maintenance or fault conditions at design wind speed or greater

5. Emergency shutdown during operation from any operating condition including:

a. Emergency stop in wind speeds less than design wind speed;

b. Emergency stop at design wind speed or greater;

c. Behavior upon automatic shutdown from overspeed at design wind speed or greater; 

and

d. Behavior upon automatic shutdown from other fault at design wind speed or greater.

6. Behavior upon loss of load

a. Response to grid outage

b. Response to grid instability

5.2 Personnel Safety Provisions

The second part of the test procedure was to evaluate provisions for personnel safety. For the 

test turbine the following issues were reviewed.

1. Safety instructions

a. Safety instructions must be available for everybody working or operating at the site or 

in the wind turbine.

b. Safety instructions must cover installation, operation, and maintenance activities.

2. Climbing facilities must be checked for proper assembly and full function.

a. Tower climbing cable or equivalent

b. Tie-off points on outside of nacelle

3. Standing places, platforms, and floors

a. Trip hazards must be avoided or marked clearly.
6

b. Platforms, floors, and walkways must be equipped with nonslip surfaces.

c. Hatches in the platforms must be lockable.

4. Electrical and grounding system

5. Emergency-stop buttons

6. Lock-out/tag-out provisions

7. Interlock on electrical cabinets

8. Presence and functioning of rotor lock and yaw lock

9. Unauthorized changing of control settings

10. Lightning protection

11. Safety signs

5.3 Dynamic Behavior

NREL staff observed the turbine at a range of operating wind speeds to note the dynamic 

behavior of the turbine, including (but not limited to) vibration, and noise.

6 Results

6.1 Control and Protection System Functions

NREL limited testing to investigation of single-fault failures and has not investigated failures 

of “safe life” components.

1

Power Control

If a second fault occurs during a critical event, unsafe results 

could occur. Neither NREL nor the IEC turbine-design requirements make judgments on 

whether such failures are likely or whether additional features in the control and protection 

system are needed to protect against such consequences.

Figure 3 shows the 1-minute mean power data and 1-second maximum power data for the 

inverter configured for standard power production. For the data collected, both the mean and 

maximum power values appear to begin leveling off at wind speeds greater than 14 m/s.

However, there are not enough data points at these wind speeds to conclude that the turbine 

exhibits power control. 

Yaw Control

This item is not applicable as the test article is a vertical axis turbine.

 

1 The IEC turbine design standard, IEC 61400-1, defines “safe life” as those components for which the 

designer has “prescribed a service life with a declared probability of failure.” These typically are 

components that transmit wind loads to the ground, such as blades, hubs, low-speed shafts, main 

bearings, main frames, yaw bearings, towers, and foundations. Failure of any of these components 

could lead to a catastrophic failure of the turbine; therefore each component should be designed with 

an appropriate safety factor. NREL has not evaluated these design characteristics and makes no 

judgment on whether appropriate safety factors have been used.
7

Rotor-Speed Control

Rotor-speed measurements over the test period indicate that the turbine system exhibits 

control over rotor speed in response to winds below about 18 m/s. Figure 4 shows both 1-

minute average and 1-second maximum rotor speed for the inverter configured for standard

power production. The maxima level off and hold at about 390 rpm. The manufacturer’s rated 

rotor speed is 380 rpm and a rotor overspeed occurs at 430 rpm. The data shows the rotor 

speed was held at less than 430 rpm.

Start-Up

Normal Operation—Wind Speed Greater Than Cut-In (4 m/s). This event was captured in 

June 2008 on the inverter configured for optimized power production. As shown in Figure 5, 

the wind speeds were slightly greater than the cut-in wind speed when the turbine started. The 

rotor speed gradually increased as the wind speeds remained constant at approximately 4 m/s. 

The turbine began producing power at a wind speed of about 4 m/s and a rotor speed of about 

180 RPM.

After Maintenance or Fault Clearance at Design Wind Speed (8.4 m/s) or Greater. This event 

occurred in June 2008 on the inverter configured for optimized power production. The turbine 

was stopped through the communication software for maintenance. After the turbine was 

enabled through the communication software, it started in winds between 9 and 13 m/s and 

began producing power. Figure 6 shows a time series of the events.

Normal Shutdown

Normal Operation—Wind Speed Decreasing to Less Than Cut-In (4 m/s). This event was 

recorded in September 2008 on the inverter configured for optimized power production. 

When the wind speed decreases to less than cut-in the turbine stops producing power and then 

free wheels. A time series of the event is shown in Figure 7.

Maintenance or Fault Conditions at Design Wind Speed (8.4 m/s) or Greater. This event was 

recorded in June 2008 on the inverter configured for optimized power production. The turbine 

was stopped through the communication software for maintenance. The wind speed was 

between 8.4 m/s and 9.0 m/s at the time the turbine was stopped. The brake was applied and 

both the detectable rotor speed and power dropped to zero within 2 seconds. Figure 8 shows a 

time series of the event.

Emergency Shutdown from Any Operating Condition During Operation

Emergency Stop in Wind Speeds Less Than Design Wind Speed (8.4 m/s). The owner’s 

manual indicates that the owner should disconnect power to the turbine to stop it in high 

winds. Thus, the emergency shutdown capability was tested by opening the dedicated 

disconnect switch that NREL installed. This event was recorded in June 2008 on the inverter 

configured for optimized power production. The wind speeds were between 4 m/s and 6 m/s 

when the disconnect switch for the turbine was opened. The brake stopped the wind turbine 

within 2 seconds. Figure 9 shows a time series of the event. 
8

Emergency Stop at Design Wind Speed (8.4 m/s) or Greater. This event was recorded in 

October 2008 on the inverter configured for standard power production in a data file 

containing one minute averages. The wind speed was between 10 m/s and 19 m/s during the 

one minute period when the disconnect switch was opened to shut the turbine down at the 

request of the manufacturer for high winds. Figure 10 shows the one minute time series of the 

event. 

Behavior Upon Automatic Shutdown from Overspeed at Design Wind Speed or Greater. No 

data was collected for this category before testing was terminated. 

Behavior Upon Automatic Shutdown from other fault at Design Wind Speed (8.4 m/s) or 

Greater. No data was collected for this category before testing was terminated.

Behavior Upon Loss of Load

Response to Grid Outage. This event was observed in June 2008 on the inverter configured 

for optimized power production. The wind speeds were between 4 m/s and 6 m/s when the 

disconnect switch for the turbine was opened. The brake stopped the wind turbine within 2 

seconds. After the switch was opened, the turbine voltage increased to 150 V before dropping 

to 0 V. Figure 9 shows a time series of the event. 

Response to Grid Instability. No data was collected for this category before testing was 

terminated.

6.2 Personnel Safety Provisions

Safety Instructions

The turbine came with an owner’s manual detailing the installation, operation, and 

maintenance procedures. NREL staff checked the manual to determine whether the safety 

instructions addressed requirements in accordance with the IEC small turbine design standard.

NREL staff found the following.

Disengage the load and/or energy sources: The manual indicates that the owner should 

disconnect power to the turbine if high winds are anticipated, if damage is suspected, or 

before servicing the turbine. The turbine was not supplied with a means of disconnecting 

power, though the one line diagram in the manual shows the turbine connected to a disconnect 

switch. NREL staff installed a dedicated disconnect switch in the data shed as a means to 

disconnect power to the turbine. 

Stop and secure the rotor: The manual states that the rotor should be secured if damage is 

suspected or if the inverter is disconnected from the generator. The manual does not provide 

specific instructions on securing the rotor. 

Stop and secure the yaw mechanism: This item is not applicable as the test article is a 

vertical axis turbine. 
9

Climb tower: The turbine is not equipped with a ladder or other means of climbing the tower. 

The owner’s manual indicates that the turbine should be lowered to perform maintenance such 

as replacing the blades or the bearings.

Climbing

The turbine tower was not intended for climbing. To service or inspect the turbine, NREL 

staff used a ladder, an aerial lift, or lowered the turbine as suggested in the owner’s manual.

Standing Places, Platforms, and Floors

The turbine does not have any standing places, platforms, or floors. 

Electrical and Grounding System

The electrical system consists of wiring from the turbine to a disconnect switch and then to a 

dedicated circuit breaker. The grounding system consists of a pole ground connected to the 

tower base. The details of the electrical and grounding system are shown in a wiring diagram 

in the owner’s manual. 

Emergency-Stop Button

The turbine was not supplied with an emergency-stop button. NREL staff stopped the turbine 

by opening the disconnect switch. Alternatively the turbine can be stopped through entering a 

command in the communications software. 

Lock-Out/Tag-Out Provisions

NREL provided a lockable switch between the grid and the turbine. The manufacturer shows

installation of a disconnect switch in the owner’s manual, though they do not specifically 

require a lockable switch. Limited procedures for de-energizing the turbine system using this 

disconnect switch are in the owner’s manual. 

Interlock on Electrical Cabinets

The turbine was not supplied with an electrical cabinet.

Safety Signs

The turbine was not provided with any safety signs, safety notices are not a part of the 

turbine’s bill of materials. NREL personnel labeled the electrical panels, and disconnects, 

indicating the voltage levels of each.

Presence and Functioning of Rotor Lock and Yaw Lock

The turbine stops the rotor with a redundant electronic brake which can be activated through 

the communication software, or a disconnect switch. As indicated in the manual, with the 

electronic brake applied the turbine maintains a low rotor speed in high winds. There are no 

instructions for locking the rotor to prevent the low rotor speed. A yaw lock is not applicable 

for the Windspire as it is a vertical axis turbine. 

Unauthorized Changing of Control Settings

The controller functions are performed by the turbine’s inverter. The inverter set points can be 

changed by communicating with the inverter wirelessly through a modem. The access mode 

in the communication software that NREL was provided with has the ability to be password 
10

protected. The control settings may be changed by the turbine owner with the communication 

software, password, and necessary code provided by Mariah Power. 

Lighting Protection

As indicated in the owner’s manual, the turbine “has a built-in lightning arrestor in the 

inverter”. During the test period no direct or nearby lightning strikes were observed.

6.3 Dynamic Behavior

Turbine operation was observed by NREL personnel for at least 5 minutes at wind speeds of 

approximately 5 m/s, 10 m/s, 15 m/s, and 20 m/s for a total observation period of at least 

1 hour. The following are a few dynamic behavior observations that were made during the test 

period:

July 21, 2008

This event was observed for the inverter configured for optimized power production. The 

leading edge tape on the turbine is beginning to separate from the blade. There is an unknown 

vibration and noise that seems to be coming from the foundation. The wind speeds were 

between 4 and 7 m/s during this observation.

October 29, 2008 

This event was observed on the inverter configured for standard power production. The 

turbine was exhibiting unsteady behavior periodically. There was a noise that seemed to come 

from the tower approximately three times per revolution. The washers at the foundation base 

were loose and the bolts and nuts on the foundation have shifted. The wind speeds were 

between 4 and 9 m/s during this observation. 
11

Figure 3. Power response to wind speed

Figure 4. Rotor-speed response to wind speed
12

Figure 5. Normal start-up, wind speeds greater than cut-in

Figure 6. Normal start-up after maintenance

0

20

40

60

80

100

120

140

160

180

200

-10

-5

0

5

10

15

20

25

30

35

40

05

101520253035404550556065707580859095

100105110115120125130135140145150155160

165170175180185190195200205210215

220225230235

rotor speed (RPM)

power (W), wind speed (m/s)

time (seconds)

Power

Wind speed

Rotor speed

0

5

10

15

20

25

-100

0

100

200

300

400

500

600

700

800

0369

121518212427303336394245485154576063666972757881848790939699

102105108111114117

wind speed (m/s)

rotor speed (RPM), power (W)

time (seconds)

Rotor speed

Power

Wind speed
13

Figure 7. Normal shut down, winds decreasing below cut in

Figure 8. Normal shut down, maintenance at design wind speed or greater

-1

0

1

2

3

4

5

6

7

-50

0

50

100

150

200

250

1 51 101 151 201 251 301 351 401 451

wind speed (m/s)

rotor speed (RPM), power (W)

time (seconds)

Power

Rotor speed

Wind speed

-2

0

2

4

6

8

10

12

14

16

18

-200

0

200

400

600

800

1000

1200

1400

0 5 10 15 20 25 30 35 40 45 50 55

wind speed (m/s), brake (V)

power (W), rotor speed (rpm)

time (seconds)

Power

Rotor speed

Wind speed

Brake
14

Figure 9. Emergency stop at wind speeds less than the design wind speed

Figure 10. Emergency stop at design wind speed or greater

-1

0

1

2

3

4

5

6

7

8

9

-50

0

50

100

150

200

250

300

350

0 2 4 6 8 10 12 14 16 18 20 22 24 26 28 30 32 34 36 38 40 42 44 46 48 50 52 54 56 58

wind speed (m/s), brake (V)

rotor speed (RPM), power (W)

time (seconds)

Power

Rotor speed

Wind speed

Brake

-5

0

5

10

15

20

25

-200

0

200

400

600

800

1000

1200

1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16

wind speed (m/s), brake (V)

rotor speed (RPM), power (W)

time (minutes)

Power

Rotor speed

Wind speed

Brake
15

7 Deviations and Exceptions

7.1 Deviations from the Standard

Testing was terminated on the Windspire before testing of all of the critical functions listed in 

the IEC standard could be completed. The overspeed protection at design wind speed or above 

function that is listed in the IEC standard as a critical function was not tested.

7.2 Exceptions to the NWTC Quality Assurance System

The data acquisition modules were used beyond the calibration due date. The modules were 

post-test calibrated and found to be in compliance within the specifications. Appendix A 

includes the post–test calibration sheets.
16

Appendix A. Instrument Calibration Sheets

Figure A.1. Power transducer calibration sheet
17

Figure A.2. Primary anemometer calibration sheet
18

Figure A.3. National Instruments 9229 data-acquisition module calibration sheet I
19

Figure A.4. National Instruments 9217 data-acquisition module calibration sheet I
20

Figure A.5. National Instruments 9205 data-acquisition module calibration sheet I
21

Figure A.6. National Instruments 9229 data-acquisition module calibration sheet II
22

Figure A.7. National Instruments 9217 data-acquisition module calibration sheet II
23

Figure A.8. National Instruments 9205 data-acquisition module calibration sheet II
F1147-E(10/2008)

REPORT DOCUMENTATION PAGE Form Approved

OMB No. 0704-0188

The public reporting burden for this collection of information is estimated to average 1 hour per response, including the time for reviewing instructions, searching existing data sources, 

gathering and maintaining the data needed, and completing and reviewing the collection of information. Send comments regarding this burden estimate or any other aspect of this 

collection of information, including suggestions for reducing the burden, to Department of Defense, Executive Services and Communications Directorate (0704-0188). Respondents 

should be aware that notwithstanding any other provision of law, no person shall be subject to any penalty for failing to comply with a collection of information if it does not display a 

currently valid OMB control number.

PLEASE DO NOT RETURN YOUR FORM TO THE ABOVE ORGANIZATION.

1. REPORT DATE (DD-MM-YYYY)

July 2010

2. REPORT TYPE

Technical Report

3. DATES COVERED (From - To)

4. TITLE AND SUBTITLE

Wind Turbine Safety and Function Test Report for the Mariah 

Windspire Wind Turbine

5a. CONTRACT NUMBER

DE-AC36-08-GO28308

5b. GRANT NUMBER

5c. PROGRAM ELEMENT NUMBER

6. AUTHOR(S)

A. Huskey, A. Bowen, and D. Jager

5d. PROJECT NUMBER

NREL/TP-500-47496

5e. TASK NUMBER

WE10.2211

5f. WORK UNIT NUMBER

7. PERFORMING ORGANIZATION NAME(S) AND ADDRESS(ES)

National Renewable Energy Laboratory

1617 Cole Blvd.

Golden, CO 80401-3393

8. PERFORMING ORGANIZATION

REPORT NUMBER

NREL/TP-500-47496

9. SPONSORING/MONITORING AGENCY NAME(S) AND ADDRESS(ES) 10. SPONSOR/MONITOR'S ACRONYM(S)

NREL

11. SPONSORING/MONITORING

AGENCY REPORT NUMBER

12. DISTRIBUTION AVAILABILITY STATEMENT

National Technical Information Service

U.S. Department of Commerce

5285 Port Royal Road

Springfield, VA 22161

13. SUPPLEMENTARY NOTES

14. ABSTRACT (Maximum 200 Words)

This test was conducted as part of the U.S. Department of Energy’s (DOE) Independent Testing project. This project 

was established to help reduce the barriers to wind energy expansion by providing independent testing results for 

small wind turbines (SWT). In total, five turbines were tested at the National Wind Technology Center (NWTC) as a 

part of this project. Safety and function testing is one of up to five tests performed on the turbines, including power 

performance, duration, noise, and power-quality tests. NWTC testing results provide manufacturers with reports that 

may be used to meet part of small wind turbine certification requirements. The test equipment includes a Mariah 

Windspire wind turbine mounted on a monopole tower. L&E Machine manufactured the turbine in the United States. 

The inverter was manufactured separately by Technology Driven Products in the United States. The system was 

installed by the NWTC site operations group with guidance and assistance from Mariah Power.

15. SUBJECT TERMS

wind turbine; Windspire; Independent testing; safety and function test; DOE; small wind turbine certification

16. SECURITY CLASSIFICATION OF: 17. LIMITATION 

OF ABSTRACT

UL

18. NUMBER 

OF PAGES

19a. NAME OF RESPONSIBLE PERSON

a. REPORT

Unclassified

b. ABSTRACT

Unclassified

c. THIS PAGE

Unclassified 19b. TELEPHONE NUMBER (Include area code)

Standard Form 298 (Rev. 8/98)

Prescribed by ANSI Std. Z39.18