[Federal Register Volume 72, Number 76 (Friday, April 20, 2007)]
[Notices]
[Pages 19891-19913]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: 07-1887]


=======================================================================
-----------------------------------------------------------------------

DEPARTMENT OF ENERGY

Office of Energy Efficiency and Renewable Energy

[Case No. CAC-013]


Energy Conservation Program for Consumer Products: Publication of 
the Petition for Waiver and Denial of the Application for Interim 
Waiver of Cascade Group, LLC From the DOE Commercial Package Air 
Conditioner and Heat Pump Test Procedures

AGENCY: Office of Energy Efficiency and Renewable Energy, Department of 
Energy.

ACTION: Notice of Petition for Waiver, denial of Application for 
Interim Waiver, and request for comments.

-----------------------------------------------------------------------

SUMMARY: Today's notice publishes the Petition for Waiver from Cascade 
Group, LLC (hereafter ``Cascade''). This Petition for Waiver (hereafter 
``Cascade Petition'') requests a waiver from the Department of Energy 
(hereafter ``DOE'') test procedure for commercial package air 
conditioners and heat pumps. In addition, today's notice denies 
Cascade's Application for Interim Waiver from the DOE test procedure 
applicable to commercial package air conditioners and heat pumps. 
Today's notice also includes an alternate test procedure DOE is 
considering. DOE is soliciting comments, data, and information with 
respect to the Cascade Petition, Cascade's Application for Interim 
Waiver, and the proposed alternate test procedure.

DATES: DOE will accept comments, data, and information until, but no 
later than May 21, 2007.

ADDRESSES: Please submit comments, identified by case number CAC-013, 
by any of the following methods:
    <bullet> Mail: Ms. Brenda Edwards-Jones, U.S. Department of Energy, 
Building Technologies Program, Mailstop EE-2J, Forrestal Building, 1000 
Independence Avenue, SW., Washington, DC 20585-0121. Telephone: (202) 
586-2945. Please submit one signed original paper copy.
    <bullet> Hand Delivery/Courier: Ms. Brenda Edwards-Jones, U.S. 
Department of Energy, Building Technologies Program, Room 1J-018, 
Forrestal Building, 1000 Independence Avenue, SW., Washington, DC 
20585.
    <bullet> E-mail: <a href="/cdn-cgi/l/email-protection#e9a4808a81888c85c7bb88908486878da98c8cc78d868cc78e869f"><span class="__cf_email__" data-cfemail="a9e4c0cac1c8ccc587fbc8d0c4c6c7cde9cccc87cdc6cc87cec6df">[email protected]</span></a>. Include either the 
case number [CAC-013], and/or ``Cascade Petition'' in the subject line 
of the message.
    <bullet> Federal eRulemaking Portal: http://www.regulations.gov. 
Follow the instructions for submitting comments.
    Instructions: All submissions received must include the agency name 
and case number for this proceeding. Submit electronic comments in 
WordPerfect, Microsoft Word, PDF, or text (ASCII) file format and avoid 
the use of special characters or any form of encryption. Wherever 
possible, include the electronic signature of the author. Absent an 
electronic signature, comments submitted electronically must be 
followed and authenticated by submitting the signed original paper 
document. DOE does not accept telefacsimiles (faxes). Any person 
submitting written comments must also send a copy of such comments to 
the petitioner. (10 CFR 431.401(d)(2)) The contact information for the 
Petitioner of today's notice is: Gary R. Scoggins, P.E., Special 
Projects Engineer, United Mechanical, Inc., P.O. Box 551206, Dallas, 
Texas 75355-1206.
    According to 10 CFR 1004.11, any person submitting information that 
he or she believes to be confidential and exempt by law from public 
disclosure should submit two copies: One copy of the document including 
all the information believed to be confidential, and one copy of the 
document with the information believed to be confidential deleted. DOE 
will make its own determination about the confidential status of the 
information and treat it according to that determination.
    Docket: For access to the docket to read the background documents 
relevant to this matter, go to the U.S. Department of Energy, Forrestal 
Building, Room 1J-018 (Resource Room of the Building Technologies 
Program), 1000 Independence Avenue, SW., Washington, DC, (202) 586-
2945, between 9 a.m. and 4 p.m., Monday through Friday, except Federal 
holidays. Available documents include the following: (1) This notice; 
(2) public comments received; (3) the Cascade Petition for Waiver and 
Application for Interim Waiver; and (4) prior DOE rulemakings regarding 
commercial central air conditioners and heat pumps. Please call Ms. 
Brenda Edwards-Jones at the above telephone number for additional 
information regarding visiting the Resource Room. Please note that 
DOE's Freedom of Information Reading Room (formerly Room 1E-190 at the 
Forrestal Building) is no longer housing rulemaking materials.

FOR FURTHER INFORMATION CONTACT: Dr. Michael G. Raymond, U.S. 
Department of Energy, Office of Energy Efficiency and Renewable Energy, 
Building Technologies Program, Mail Stop EE-2J, Forrestal Building, 
1000 Independence Avenue, SW., Washington, DC 20585-

[[Page 19892]]

0121, (202) 586-9611; e-mail: Michael.Raymond.ee.doe.gov; or Francine 
Pinto, Esq., U.S. Department of Energy, Office of General Counsel, Mail 
Stop GC-72, Forrestal Building, 1000 Independence Avenue, SW., 
Washington, DC 20585-0103, (202) 586-9507; e-mail: 
<a href="/cdn-cgi/l/email-protection#4e083c2f202d27202b601e27203a210e263f602a212b60292138"><span class="__cf_email__" data-cfemail="6a2c180b040903040f443a03041e052a021b440e050f440d051c">[email protected]</span></a>.

SUPPLEMENTARY INFORMATION:

I. Background and Authority
II. Petition for Waiver
III. Application for Interim Waiver
IV. Alternate Test Procedure
V. Summary and Request for Comments

I. Background and Authority

    Title III of the Energy Policy and Conservation Act (EPCA) sets 
forth a variety of provisions concerning energy efficiency. Part C of 
Title III (42 U.S.C. 6311-6317) provides for an energy efficiency 
program entitled ``Certain Industrial Equipment,'' and includes 
commercial air conditioning equipment, packaged boilers, water heaters, 
and other types of commercial equipment.
    Today's notice involves commercial equipment under Part C, which 
specifically provides for definitions, test procedures, labeling 
provisions, energy conservation standards, and the authority to require 
information and reports from manufacturers. With respect to test 
procedures, Part C generally authorizes the Secretary of Energy to 
prescribe test procedures that are reasonably designed to produce 
results which reflect energy efficiency, energy use and estimated 
operating costs, and that are not unduly burdensome to conduct. (42 
U.S.C. 6314(a)(2)).
    For commercial package air conditioning and heating equipment, EPCA 
provides that the test procedures shall be those generally accepted 
industry testing procedures or rating procedures developed or 
recognized by the Air-Conditioning and Refrigeration Institute (ARI) or 
by the American Society of Heating, Refrigerating and Air Conditioning 
Engineers (ASHRAE), as referenced in ASHRAE/IES Standard 90.1 and in 
effect on June 30, 1992. (42 U.S.C. 6314(a)(4)(A)) This section also 
provides for the Secretary of Energy to amend the test procedure for a 
product if the industry test procedure is amended, unless the Secretary 
determines that such a modified test procedure does not meet the 
statutory criteria. (42 U.S.C. 6314(a)(4)(B)) On October 21, 2004, DOE 
published a direct final rule, effective December 20, 2004, adopting 
ARI Standard 210/240-2003 for small commercial package air conditioning 
and heating equipment with capacities < 65,000 Btu/h and ARI Standard 
340/360-2000 for large commercial package air conditioning and heating 
equipment with capacities >= 135,000 Btu/h and < 240,000 Btu/h and 
small commercial package air conditioning and heating equipment with 
capacities >= 65,000 Btu/h and < 135,000 Btu/h. 69 FR 61962, October 
21, 2004. According to Cascade, both ARI Standard 340/360-2000 and ARI 
Standard 210/240-2003 are applicable to Cascade's Cascade Energy Saver 
(CES) products. However, Cascade only seeks a waiver from ARI Standard 
210/240-2003.
    DOE's regulations set forth under 10 CFR 431.401 contain provisions 
allowing a person to seek a waiver from the test procedure requirements 
for commercial equipment. The waiver provisions allow the Assistant 
Secretary for Energy Efficiency and Renewable Energy (hereafter 
``Assistant Secretary'') to temporarily waive test procedures for a 
particular basic model when a petitioner shows that the basic model 
contains one or more design characteristics which either prevent 
testing according to the prescribed test procedures, or when the 
prescribed test procedures may evaluate the basic model in a manner so 
unrepresentative of its true energy consumption as to provide 
materially inaccurate comparative data. 10 CFR 431.401(a)(1). The 
Assistant Secretary may grant the waiver subject to conditions, 
including adherence to alternate test procedures. 10 CFR 431.401(f)(4). 
Petitioners are to include in their petition any alternate test 
procedures known to evaluate the basic model in a manner representative 
of its energy consumption. 10 CFR 431.401(b)(1)(iii). Waivers generally 
remain in effect until final test procedure amendments become 
effective, thereby resolving the problem that is the subject of the 
waiver. 10 CFR 431.401(g).
    The waiver process also allows the Assistant Secretary to grant an 
interim waiver from test procedure requirements to manufacturers who 
have petitioned DOE for a waiver of such prescribed test procedures. 10 
CFR 431.401(a)(2). An interim waiver remains in effect for a period of 
180 days or until DOE issues its determination on the petition for 
waiver, whichever is sooner, and may be extended for an additional 180 
days, if necessary. 10 CFR 431.401(e)(4).

II. Petition for Waiver

    On July 22, 2005, Cascade filed the Cascade Petition for Waiver and 
its Application for an Interim Waiver from the test procedures 
applicable to commercial package air conditioning and heating 
equipment. On May 26, 2006, Cascade filed an amended Petition for 
Waiver listing all the basic models for which Cascade seeks a waiver. 
In particular, Cascade requested a waiver from the commercial test 
procedures contained in ARI Standard 210/240-2003 for the system 
combinations listed in Table 1, attached to its amended Petition.
    Cascade seeks a waiver from the test procedures in ARI Standard 
210/240-2003 and asserts that the design characteristics of the CES 
systems prevent testing according to these prescribed test procedures. 
In particular, Cascade states that the CES indoor-coil blower models 
have more than one blower per coil and up to and as many as eight 
blowers that operate independently. Cascade claims that its products do 
not conform to the test procedures in ARI Standard 210/240-2003, 
because these test procedures are based on a system with only one 
indoor-coil blower.
    Cascade asserts that with slight modifications to ARI 210/240 
procedures, CES units can be tested and that such testing can provide 
measurements to satisfactorily determine the Seasonal Energy Efficiency 
Ratio (SEER) and the Heating Seasonal Performance Factor (HSPF). 
Cascade included in its petition sample SEER calculations, sample test 
procedures used to derive the SEER calculations, and sample test data. 
The testing, contracted by Cascade to Texas A&M University Energy 
Services Laboratory (hereafter ``TAMU-ESL''), provides data on a system 
with two 2.5-ton Amana RHF 030 heat pump units of SEER 12 connected to 
a dual-circuit evaporator coil, followed by a plenum housing 8 blowers 
operated by a control system. Using a test procedure based on ARI 210/
240, TAMU-ESL calculated a SEER value of 18.1 and an HSPF of 9.5. 
Details of the testing are provided in the Cascade Petition, published 
in full, below.

III. Application for Interim Waiver

    Cascade also requested immediate relief through its Application for 
Interim Waiver to avert undue economic hardship. According to DOE 
regulations, an interim waiver may be granted if it is determined that 
the applicant will experience economic hardship if the application for 
interim waiver is denied, if it appears likely that the petition for 
waiver will be granted, and/or the Assistant Secretary determines that 
it would be desirable for public policy reasons to grant immediate 
relief

[[Page 19893]]

pending a determination of the petition for waiver. 10 CFR 
431.401(e)(3).
    Cascade's Application for Interim Waiver does not provide 
sufficient information to evaluate what, if any, economic impact or 
competitive disadvantage Cascade will likely experience absent a 
favorable determination on its application. It also does not provide 
sufficient information to determine if there are public policy reasons 
to grant immediate relief. Furthermore, DOE has never granted a 
previous waiver for a similar product design. Thus, the likelihood of 
granting the waiver is unclear until further information and comment is 
provided.
    Therefore, Cascade's Application for an Interim Waiver from the DOE 
test procedure for its CES products is denied. Hence, it is ordered 
that: The Application for Interim Waiver filed by Cascade is hereby 
denied for Cascade's CES air conditioners and central air conditioning 
heat pumps.
    This denial of Cascade's Application for Interim Waiver is based 
upon the presumed validity of statements and allegations submitted by 
the company. This denial of Interim Waiver may be modified if DOE 
receives information that justifies granting an Interim Waiver.

IV. Alternate Test Procedure

    DOE will make its judgment on the Cascade Petition after the period 
for public comment ends. However, should DOE grant Cascade a waiver 
from the applicable test procedures, DOE would likely prescribe an 
alternate test procedure. Manufacturers face restrictions with respect 
to making representations about the energy consumption and energy 
consumption costs of products covered by EPCA. (42 U.S.C. 6314(d)) 
Consistent representations are important for manufacturers to make 
claims about the energy efficiency of their products. For example, they 
are necessary to determine compliance with state and local energy codes 
and regulatory requirements, and can provide valuable consumer 
purchasing information. Therefore, DOE is considering an alternate test 
procedure for Cascade. DOE is publishing the proposed alternate test 
procedure in this notice to account for the potential need for an 
alternate test procedure and to allow the public to comment on a 
proposed alternate test procedure.
    Cascade included a description of an alternate test procedure and 
test data for a sample system in its Petition. DOE is considering 
prescribing an alternate test procedure that takes into account the 
information Cascade provided in the petition. In particular, the 
proposed alternate test procedure would require Cascade to test units 
according to ARI Standard 210/240-2003, but permit Cascade to use 
alternate requirements when testing systems that have multiple fans per 
indoor coil.\1\ Cascade may test systems with multiple indoor fans that 
jointly provide the total indoor-coil airflow rate required for the 
capacity being tested, however, Cascade would be required to adhere to 
the airflow requirement of section 6.1.3.3 of ARI Standard 210/240-
2003, which sets an upper limit on indoor-coil airflow according to 
system capacity.\2\ During testing, the individual indoor fans would 
each deliver an equal portion of the total required airflow.
---------------------------------------------------------------------------

    \1\ For example, according to a 450 cfm/ton requirement, a 5 ton 
unit would be permitted to have an airflow rate of 2,250 cfm or 
lower. If that system were to operate at 2,000 cfm and have 8 fans, 
each fan would blow 250 cfm. In addition, if that same system were 
to operate at partial load with 2.5 tons of capacity, the tester 
could operate 4 fans with each fan blowing 250 cfm.
    \2\ For example, section 6.1.3.3 requires equipment with indoor 
fans intended for use with field installed duct systems to be rated 
at the indoor-coil airflow rate of equal to or less than 37.5 SCFM 
per 1,000 Btu/h of rated capacity.
---------------------------------------------------------------------------

    DOE generally agrees with TAMU-ESL's testing and analysis of a 
system with a CES 5-ton, 8-zone unit connected to an Amana RHF030 heat 
pump with a SEER of 12-14. As each Amana RHF030 heat pump uses a 
single-speed compressor, DOE agrees with TAMU-ESL's choice to treat the 
system as a two-speed blower with a two-stage compressor and test the 
system according to A2.2.2 and A2.1.3. Furthermore, DOE agrees with 
TAMU-ESL's decision to ensure a total indoor-coil airflow rate of 
around 2,000 cfm with eight blowers providing 250 cfm each, when 
operating the system at a full capacity. For low-speed conditions, 
TAMU-ESL operated the system at a 2.5-ton capacity and ensured a total 
indoor-coil airflow rate of around 1,000 cfm, with four blowers 
providing 250 cfm each.
    However, it is not clear why TAMU-ESL conducted Test C for full 
load operation only, though section A3.1.3 indicates that if one 
chooses to perform Test C, the system must be tested at low-speed. 
Furthermore, for certification, testing conditions must fall within the 
applicable tolerances provided in ARI 210/240-2003. Finally, while DOE 
generally approves of the TAMU-ESL method to test a CES multi-blower 
unit paired with two Amana RHF030 heat pumps, DOE would expect Cascade 
to test its units according to those appropriate tests, procedures and 
conditions generally stated in ARI 210/240-2003. For example, testing 
of a CES unit paired to a variable-speed compressor should follow the 
procedures and requirements described for a system with a variable-
speed compressor in A2.1.6.
    Given consideration of the information provided to DOE in the 
Cascade Petition, DOE is considering the following alternate test 
procedure:
    Alternate test procedure. Cascade shall be required to test the 
products covered under this Waiver according to the prescribed tests, 
conditions, and procedures referenced in ARI Standard 210/240-2003, 
except that Cascade shall be permitted to test systems with indoor 
units that have multiple fans. As such, Cascade shall be required to 
meet the usual indoor-coil airflow rate requirements of ARI Standard 
210/240-2003, section 6.1.3.3. However, tested units may run multiple 
indoor-coil fans which collectively meet the required indoor-coil 
airflow rates per capacity. To determine the level at which to operate 
the indoor fans during testing, Cascade may divide the total indoor-
coil airflow rate at full load, by the number of indoor fans in the 
tested system. During testing, Cascade shall run the indoor fans at 
this level, and may decide how many indoor fans to operate by dividing 
the total indoor-coil airflow required at the capacity being tested by 
the indoor fan level, as determined above. Cascade may make 
representations of the CES products covered in this Waiver, consistent 
with the provisions outlined in this alternate test procedure.

V. Summary and Request for Comments

    Today's notice announces the Cascade Petition for Waiver and denies 
Cascade's Application for Interim Waiver from the test procedures 
applicable to Cascade's CES air conditioner and heat pump units. DOE is 
publishing the Cascade Petition for Waiver in its entirety. The Cascade 
Petition contains no confidential information. Furthermore, today's 
notice includes an alternate test procedure that the DOE is considering 
including in the subsequent Decision and Order, should DOE decide to 
grant Cascade a Waiver.
    DOE is interested in receiving comments on all aspects of this 
notice. DOE is particularly interested in receiving comments and views 
of interested parties concerning whether to grant the Cascade Petition 
and regarding the proposed alternate test procedure. Specifically, DOE 
would like to receive comment on the following questions:
    <bullet> Does this alternate test procedure adequately specify how 
to handle

[[Page 19894]]

airflows when testing a system with multiple blowers?
    <bullet> In the proposed alternate test procedure, fans are to run 
at a set cfm per fan throughout a test. Is this appropriate or should 
DOE allow fans to run at different cfm's throughout a test while still 
meeting the required overall indoor-coil airflow rate according to 
capacity?
    <bullet> Cascade states that the current test procedure is not 
specific about the method of configuring a dual-circuited evaporator 
coil to blowers. However, Cascade does not propose specific language. 
Does the alternate test procedure proposed in this notice need to 
specifically address configurations of dual-evaporator coils and coil-
blowers?
    <bullet> DOE is interested in receiving general comments on 
possible modifications to any test procedures or alternative rating 
methods that DOE could use to fairly represent the energy efficiency of 
Cascade's CES products.
    Any person submitting written comments must also send a copy of 
such comments to the Petitioner, whose contact information is cited 
above. 10 CFR 431.201(d)(2).

    Issued in Washington, DC, on April 9, 2007.
Alexander A. Karsner,
Assistant Secretary, Energy Efficiency and Renewable Energy.

Petition of Waiver Submitted by: Cascade Group, LLC, General partner 
for Cascade Manufacturing, LP; 11540 Plano Road, Dallas, Texas 75243, 
1-214-341-9300, Patents 5,701,750 and 6,792,768, 05/26/06, Amended 04/
16/07

IDENTIFICATION OF BASIC SIZES AND MODELS OF CES
    THE CES IS SOLD IN THE FOLLOWING SIZES AND MODELS:
    Number of Blowers
DESIGN CHARACTERISTICS CONSTITUTING THE GROUNDS FOR PETITION
SPECIFIC REQUIREMENTS SOUGHT TO BE WAIVED
DISCUSSION IN DETAILS FOR THE REQUESTED WAIVER
IDENTIFICATION OF MANUFACTURERS WITH SIMILAR DESIGN CHARACTERISTICS
ALTERNATIVE TEST PROCEDURES TO EVALUATE ENERGY CONSUMPTION 
CHARACTERISTICS

Identification of Basic Sizes and Models of CES

    The CES is sold in the following sizes and models:

    Example 1: Model CES 1-2-2-H-5kw is a size 2 Ton evaporative coil 
matched with a single 2 ton heat pump, with 2 blowers, horizontal 
configuration with 5 kW auxiliary heat.
    Example 2: Model CES 2-2.5-8-V-10kw is a size 6 ton 50/50 split 
evaporative coil matched with two 2.5 ton heat pumps, with 8 blowers, 
vertical upflow configuration with 10 kW auxiliary heat.

    Note: Table 1 below only shows horizontal configurations. There 
is not a difference in performance. A vertical unit could have been 
easily represented.


                                                                         Table 1
--------------------------------------------------------------------------------------------------------------------------------------------------------
      Tons          Qty of heat                                                      Number of blowers
-----------------    pump units   ----------------------------------------------------------------------------------------------------------------------
                 -----------------
        2             1-2 Ton             2                3                4
--------------------------------------------------------------------------------------------------------------------------------------------------------
                  ...............  CES 1-2-2-H-5KW  CES 1-2-3-H-5KW  CES 1-2-4-H-
                                                                      5KW.
--------------------------------------------------------------------------------------------------------------------------------------------------------
2.5               1-2.5 T          2                3                4
--------------------------------------------------------------------------------------------------------------------------------------------------------
                  ...............  CES 1-2.5-2-H-   CES 1-2.5-3-H-   CES 1-2.5-4-H-
                                    5KW              5KW              5KW.
--------------------------------------------------------------------------------------------------------------------------------------------------------
3                 2-1.5 T          2                3                4
--------------------------------------------------------------------------------------------------------------------------------------------------------
                  ...............  CES 1-3-2-H-5KW  CES 1-3-3-H-5KW  CES 1-3-4-H-
                                                                      5KW.
--------------------------------------------------------------------------------------------------------------------------------------------------------
4                 2-2 T            2                3                4                5                6                7                8
--------------------------------------------------------------------------------------------------------------------------------------------------------
                  ...............  CES 2-2-2-H-     CES 2-2-3-H-     CES 2-2-4-H-     CES 2-2-5-H-     CES 2-2-6-H-     CES 2-2-7-H-     CES 2-2-8-H-
                                    10KW             10KW             10KW             10KW             10KW             10KW             10KW.
--------------------------------------------------------------------------------------------------------------------------------------------------------
5                 2-2.5 T          2                3                4                5                6                7                8
--------------------------------------------------------------------------------------------------------------------------------------------------------
                  ...............  CES 2-2.5-2-H-   CES 2-2.5-3-H-   CES 2-2.5-4-H-   CES 2-2.5-5-H-   CES2-2.5-6-H-10  CES 2-2.5-7-H-   CES 2-2.5-8-H-
                                    10KW             10KW             10KW             10KW             KW               10KW             10KW.
--------------------------------------------------------------------------------------------------------------------------------------------------------

    Table 1-1 below shows the system combinations of Cascade Indoor 
Units with the respective outdoor heat units sorted by manufacturer 
with the associated model number.

                                     Table 1-1.--Combinations of Indoor-Outdoor Units That Are Subject to the Waiver
--------------------------------------------------------------------------------------------------------------------------------------------------------
                               Indoor unit                                                                 Outdoor unit
--------------------------------------------------------------------------------------------------------------------------------------------------------
                                                                                                          Qty of outside
            Manufacturer                    Cascade model          Tons    System heat pump manufacturer     units per               Model No.
                                                                                                           cascade unit
--------------------------------------------------------------------------------------------------------------------------------------------------------
Cascade Manufacturing, L.P.          CES 1-2-2.................        2  Amana.........................               1  ASH130241A.
 (Cascade).
Cascade............................  CES 1-2-2.................        2  Aire-Flo......................               1  2HP13(B,L)24P-1.
Cascade............................  CES 1-2-2.................        2  AirPro........................               1  FRHS0241CD.

[[Page 19895]]

 
Cascade............................  CES 1-2-2.................        2  American Standard.............               1  2A6B3024A1.
Cascade............................  CES 1-2-2.................        2  Bryant........................               1  213ANA024-A.
Cascade............................  CES 1-2-2.................        2  Carrier.......................               1  25HBA324A30.
Cascade............................  CES 1-2-2.................        2  Coleman.......................               1  DRHS0241BD.
Cascade............................  CES 1-2-2.................        2  Ducane........................               1  2HP13(B,L)24P-1.
Cascade............................  CES 1-2-2.................        2  Fedders.......................               1  CH24ABD1VF.
Cascade............................  CES 1-2-2.................        2  Frigidaire....................               1  FT3BD-024K.
Cascade............................  CES 1-2-2.................        2  Gibson........................               1  GT3BD-024K.
Cascade............................  CES 1-2-2.................        2  Goodman.......................               1  GSH130241A.
Cascade............................  CES 1-2-2.................        2  Lennox........................               1  12HPB24-P.
Cascade............................  CES 1-2-2.................        2  Luxaire.......................               1  EABC-F024S.
Cascade............................  CES 1-2-2.................        2  Maytag........................               1  PSH1BC024K.
Cascade............................  CES 1-2-2.................        2  Rheem.........................               1  13PJA24.
Cascade............................  CES 1-2-2.................        2  Ruud..........................               1  13PJA24.
Cascade............................  CES 1-2-2.................        2  Tappan........................               1  FT3BD-024K.
Cascade............................  CES 1-2-2.................        2  Trane.........................               1  2TWB3024A1.
Cascade............................  CES 1-2-2.................        2  York..........................               1  E1RC024S06.
Cascade............................  CES 1-2-2.................        2  Westinghouse..................               1  FT3BD-024K.
Cascade............................  CES 1-2-2.................        2  Whirlpool.....................               1  W2H324A-1A.
Cascade............................  CES 1-2-3.................        2  Amana.........................               1  ASH130241A.
Cascade............................  CES 1-2-3.................        2  Aire-Flo......................               1  2HP13(B,L)24P-1.
Cascade............................  CES 1-2-3.................        2  AirPro........................               1  FRHS0241CD.
Cascade............................  CES 1-2-3.................        2  American Standard.............               1  2A6B3024A1.
Cascade............................  CES 1-2-3.................        2  Bryant........................               1  213ANA024-A.
Cascade............................  CES 1-2-3.................        2  Carrier.......................               1  25HBA324A30.
Cascade............................  CES 1-2-3.................        2  Coleman.......................               1  DRHS0241BD.
Cascade............................  CES 1-2-3.................        2  Ducane........................               1  2HP13(B,L)24P-1.
Cascade............................  CES 1-2-3.................        2  Fedders.......................               1  CH24ABD1VF.
Cascade............................  CES 1-2-3.................        2  Frigidaire....................               1  FT3BD-024K.
Cascade............................  CES 1-2-3.................        2  Gibson........................               1  GT3BD-024K.
Cascade............................  CES 1-2-3.................        2  Goodman.......................               1  GSH130241A.
Cascade............................  CES 1-2-3.................        2  Lennox........................               1  12HPB24-P.
Cascade............................  CES 1-2-3.................        2  Luxaire.......................               1  EABC-F024S.
Cascade............................  CES 1-2-3.................        2  Maytag........................               1  PSH1BC024K.
Cascade............................  CES 1-2-3.................        2  Rheem.........................               1  13PJA24.
Cascade............................  CES 1-2-3.................        2  Ruud..........................               1  13PJA24.
Cascade............................  CES 1-2-3.................        2  Tappan........................               1  FT3BD-024K.
Cascade............................  CES 1-2-3.................        2  Trane.........................               1  2TWB3024A1.
Cascade............................  CES 1-2-3.................        2  York..........................               1  E1RC024S06.
Cascade............................  CES 1-2-3.................        2  Westinghouse..................               1  FT3BD-024K.
Cascade............................  CES 1-2-3.................        2  Whirlpool.....................               1  W2H324A-1A.
Cascade............................  CES 1-2-4.................        2  Amana.........................               1  ASH130241A.
Cascade............................  CES 1-2-4.................        2  Aire-Flo......................               1  2HP13(B,L)24P-1.
Cascade............................  CES 1-2-4.................        2  AirPro........................               1  FRHS0241CD.
Cascade............................  CES 1-2-4.................        2  American Standard.............               1  2A6B3024A1.
Cascade............................  CES 1-2-4.................        2  Bryant........................               1  213ANA024-A.
Cascade............................  CES 1-2-4.................        2  Carrier.......................               1  25HBA324A30.
Cascade............................  CES 1-2-4.................        2  Coleman.......................               1  DRHS0241BD.
Cascade............................  CES 1-2-4.................        2  Ducane........................               1  2HP13(B,L)24P-1.
Cascade............................  CES 1-2-4.................        2  Fedders.......................               1  CH24ABD1VF.
Cascade............................  CES 1-2-4.................        2  Frigidaire....................               1  FT3BD-024K.
Cascade............................  CES 1-2-4.................        2  Gibson........................               1  GT3BD-024K.
Cascade............................  CES 1-2-4.................        2  Goodman.......................               1  GSH130241A.
Cascade............................  CES 1-2-4.................        2  Lennox........................               1  12HPB24-P.
Cascade............................  CES 1-2-4.................        2  Luxaire.......................               1  EABC-F024S.
Cascade............................  CES 1-2-4.................        2  Maytag........................               1  PSH1BC024K.
Cascade............................  CES 1-2-4.................        2  Rheem.........................               1  13PJA24.
Cascade............................  CES 1-2-4.................        2  Ruud..........................               1  13PJA24.
Cascade............................  CES 1-2-4.................        2  Tappan........................               1  FT3BD-024K.
Cascade............................  CES 1-2-4.................        2  Trane.........................               1  2TWB3024A1.
Cascade............................  CES 1-2-4.................        2  York..........................               1  E1RC024S06.
Cascade............................  CES 1-2-4.................        2  Westinghouse..................               1  FT3BD-024K.
Cascade............................  CES 1-2-4.................        2  Whirlpool.....................               1  W2H324A-1A.
Cascade............................  CES 1-2.5-2...............      2.5  Amana.........................               1  ASH130301A.
Cascade............................  CES 1-2.5-2...............      2.5  Aire-Flo......................               1  2HP13(B,L)30P-1.
Cascade............................  CES 1-2.5-2...............      2.5  AirPro........................               1  FRHS0301CD.
Cascade............................  CES 1-2.5-2...............      2.5  American Standard.............               1  2A6B3030A1.
Cascade............................  CES 1-2.5-2...............      2.5  Bryant........................               1  213ANA030-A.

[[Page 19896]]

 
Cascade............................  CES 1-2.5-2...............      2.5  Carrier.......................               1  25HBA330A30.
Cascade............................  CES 1-2.5-2...............      2.5  Coleman.......................               1  DRHS0301BD.
Cascade............................  CES 1-2.5-2...............      2.5  Ducane........................               1  2HP13(B,L)30P-1.
Cascade............................  CES 1-2.5-2...............      2.5  Fedders.......................               1  CH30ABD1VF.
Cascade............................  CES 1-2.5-2...............      2.5  Frigidaire....................               1  FT3BD-030K.
Cascade............................  CES 1-2.5-2...............      2.5  Gibson........................               1  GT3BD-030K.
Cascade............................  CES 1-2.5-2...............      2.5  Goodman.......................               1  CPLT30-1.
Cascade............................  CES 1-2.5-2...............      2.5  Lennox........................               1  12HPB30-P.
Cascade............................  CES 1-2.5-2...............      2.5  Luxaire.......................               1  EABC-F030S.
Cascade............................  CES 1-2.5-2...............      2.5  Maytag........................               1  DT3BD-030K.
Cascade............................  CES 1-2.5-2...............      2.5  Rheem.........................               1  13PJA30.
Cascade............................  CES 1-2.5-2...............      2.5  Ruud..........................               1  13PJA30.
Cascade............................  CES 1-2.5-2...............      2.5  Tappan........................               1  FT3BD-030K.
Cascade............................  CES 1-2.5-2...............      2.5  Trane.........................               1  2TWB3030A1.
Cascade............................  CES 1-2.5-2...............      2.5  York..........................               1  E1RC030S06.
Cascade............................  CES 1-2.5-2...............      2.5  Westinghouse..................               1  FT3BD-030K.
Cascade............................  CES 1-2.5-2...............      2.5  Whirlpool.....................               1  WGH430A.
Cascade............................  CES 1-2.5-3...............      2.5  Amana.........................               1  ASH130301A.
Cascade............................  CES 1-2.5-3...............      2.5  Aire-Flo......................               1  2HP13(B,L)30P-1.
Cascade............................  CES 1-2.5-3...............      2.5  AirPro........................               1  FRHS0301CD.
Cascade............................  CES 1-2.5-3...............      2.5  American Standard.............               1  2A6B3030A1.
Cascade............................  CES 1-2.5-3...............      2.5  Bryant........................               1  213ANA030-A.
Cascade............................  CES 1-2.5-3...............      2.5  Carrier.......................               1  25HBA330A30.
Cascade............................  CES 1-2.5-3...............      2.5  Coleman.......................               1  DRHS0301BD.
Cascade............................  CES 1-2.5-3...............      2.5  Ducane........................               1  2HP13(B,L)30P-1.
Cascade............................  CES 1-2.5-3...............      2.5  Fedders.......................               1  CH30ABD1VF.
Cascade............................  CES 1-2.5-3...............      2.5  Frigidaire....................               1  FT3BD-030K.
Cascade............................  CES 1-2.5-3...............      2.5  Gibson........................               1  GT3BD-030K.
Cascade............................  CES 1-2.5-3...............      2.5  Goodman.......................               1  CPLT30-1.
Cascade............................  CES 1-2.5-3...............      2.5  Lennox........................               1  12HPB30-P.
Cascade............................  CES 1-2.5-3...............      2.5  Luxaire.......................               1  EABC-F030S.
Cascade............................  CES 1-2.5-3...............      2.5  Maytag........................               1  DT3BD-030K.
Cascade............................  CES 1-2.5-3...............      2.5  Rheem.........................               1  13PJA30.
Cascade............................  CES 1-2.5-3...............      2.5  Ruud..........................               1  13PJA30.
Cascade............................  CES 1-2.5-3...............      2.5  Tappan........................               1  FT3BD-030K.
Cascade............................  CES 1-2.5-3...............      2.5  Trane.........................               1  2TWB3030A1.
Cascade............................  CES 1-2.5-3...............      2.5  York..........................               1  E1RC030S06.
Cascade............................  CES 1-2.5-3...............      2.5  Westinghouse..................               1  FT3BD-030K.
Cascade............................  CES 1-2.5-3...............      2.5  Whirlpool.....................               1  WGH430A.
Cascade............................  CES 1-2.5-4...............      2.5  Amana.........................               1  ASH130301A.
Cascade............................  CES 1-2.5-4...............      2.5  Aire-Flo......................               1  2HP13(B,L)30P-1.
Cascade............................  CES 1-2.5-4...............      2.5  AirPro........................               1  FRHS0301CD.
Cascade............................  CES 1-2.5-4...............      2.5  American Standard.............               1  2A6B3030A1.
Cascade............................  CES 1-2.5-4...............      2.5  Bryant........................               1  213ANA030-A.
Cascade............................  CES 1-2.5-4...............      2.5  Carrier.......................               1  25HBA330A30.
Cascade............................  CES 1-2.5-4...............      2.5  Coleman.......................               1  DRHS0301BD.
Cascade............................  CES 1-2.5-4...............      2.5  Ducane........................               1  2HP13(B,L)30P-1.
Cascade............................  CES 1-2.5-4...............      2.5  Fedders.......................               1  CH30ABD1VF.
Cascade............................  CES 1-2.5-4...............      2.5  Frigidaire....................               1  FT3BD-030K.
Cascade............................  CES 1-2.5-4...............      2.5  Gibson........................               1  GT3BD-030K.
Cascade............................  CES 1-2.5-4...............      2.5  Goodman.......................               1  CPLT30-1.
Cascade............................  CES 1-2.5-4...............      2.5  Lennox........................               1  12HPB30-P.
Cascade............................  CES 1-2.5-4...............      2.5  Luxaire.......................               1  EABC-F030S.
Cascade............................  CES 1-2.5-4...............      2.5  Maytag........................               1  DT3BD-030K.
Cascade............................  CES 1-2.5-4...............      2.5  Rheem.........................               1  13PJA30.
Cascade............................  CES 1-2.5-4...............      2.5  Ruud..........................               1  13PJA30.
Cascade............................  CES 1-2.5-4...............      2.5  Tappan........................               1  FT3BD-030K.
Cascade............................  CES 1-2.5-4...............      2.5  Trane.........................               1  2TWB3030A1.
Cascade............................  CES 1-2.5-4...............      2.5  York..........................               1  E1RC030S06.
Cascade............................  CES 1-2.5-4...............      2.5  Westinghouse..................               1  FT3BD-030K.
Cascade............................  CES 1-2.5-4...............      2.5  Whirlpool.....................               1  WGH430A.
Cascade............................  CES-2-1.5-2...............        3  Amana.........................               2  ASH130181A.
Cascade............................  CES-2-1.5-2...............        3  Aire-Flo......................               2  2HP13(B,L)18P-1.
Cascade............................  CES-2-1.5-2...............        3  AirPro........................               2  DRHS0181BD.
Cascade............................  CES-2-1.5-2...............        3  American Standard.............               2  2A6B3018A1.
Cascade............................  CES-2-1.5-2...............        3  Bryant........................               2  213ANA018-A.
Cascade............................  CES-2-1.5-2...............        3  Carrier.......................               2  25HBA318A30.
Cascade............................  CES-2-1.5-2...............        3  Coleman.......................               2  DRHS0181BD.

[[Page 19897]]

 
Cascade............................  CES-2-1.5-2...............        3  Ducane........................               2  2HP13(B,L)18P-1.
Cascade............................  CES-2-1.5-2...............        3  Fedders.......................               2  CH18ABD1VF.
Cascade............................  CES-2-1.5-2...............        3  Frigidaire....................               2  FT3BD-018K.
Cascade............................  CES-2-1.5-2...............        3  Gibson........................               2  GT3BD-018K.
Cascade............................  CES-2-1.5-2...............        3  Goodman.......................               2  GSH130181A.
Cascade............................  CES-2-1.5-2...............        3  Lennox........................               2  12HPB18-P.
Cascade............................  CES-2-1.5-2...............        3  Luxaire.......................               2  EABC-F018S.
Cascade............................  CES-2-1.5-2...............        3  Maytag........................               2  DT5BD-018K.
Cascade............................  CES-2-1.5-2...............        3  Rheem.........................               2  13PJA18.
Cascade............................  CES-2-1.5-2...............        3  Ruud..........................               2  UPNE-018JZ.
Cascade............................  CES-2-1.5-2...............        3  Tappan........................               2  FT3BD-018K.
Cascade............................  CES-2-1.5-2...............        3  Trane.........................               2  2TWB3018A1.
Cascade............................  CES-2-1.5-2...............        3  York..........................               2  E1RC018S06.
Cascade............................  CES-2-1.5-2...............        3  Westinghouse..................               2  W2H318A-1A.
Cascade............................  CES-2-1.5-2...............        3  Whirlpool.....................               2  W2H318A-1A.
Cascade............................  CES-2-1.5-3...............        3  Amana.........................               2  ASH130181A.
Cascade............................  CES-2-1.5-3...............        3  Aire-Flo......................               2  2HP13(B,L)18P-1.
Cascade............................  CES-2-1.5-3...............        3  AirPro........................               2  DRHS0181BD.
Cascade............................  CES-2-1.5-3...............        3  American Standard.............               2  2A6B3018A1.
Cascade............................  CES-2-1.5-3...............        3  Bryant........................               2  213ANA018-A.
Cascade............................  CES-2-1.5-3...............        3  Carrier.......................               2  25HBA318A30.
Cascade............................  CES-2-1.5-3...............        3  Coleman.......................               2  DRHS0181BD.
Cascade............................  CES-2-1.5-3...............        3  Ducane........................               2  2HP13(B,L)18P-1.
Cascade............................  CES-2-1.5-3...............        3  Fedders.......................               2  CH18ABD1VF.
Cascade............................  CES-2-1.5-3...............        3  Frigidaire....................               2  FT3BD-018K.
Cascade............................  CES-2-1.5-3...............        3  Gibson........................               2  GT3BD-018K.
Cascade............................  CES-2-1.5-3...............        3  Goodman.......................               2  GSH130181A.
Cascade............................  CES-2-1.5-3...............        3  Lennox........................               2  12HPB18-P.
Cascade............................  CES-2-1.5-3...............        3  Luxaire.......................               2  EABC-F018S.
Cascade............................  CES-2-1.5-3...............        3  Maytag........................               2  DT5BD-018K.
Cascade............................  CES-2-1.5-3...............        3  Rheem.........................               2  13PJA18.
Cascade............................  CES-2-1.5-3...............        3  Ruud..........................               2  UPNE-018JZ.
Cascade............................  CES-2-1.5-3...............        3  Tappan........................               2  FT3BD-018K.
Cascade............................  CES-2-1.5-3...............        3  Trane.........................               2  2TWB3018A1.
Cascade............................  CES-2-1.5-3...............        3  York..........................               2  E1RC018S06.
Cascade............................  CES-2-1.5-3...............        3  Westinghouse..................               2  W2H318A-1A.
Cascade............................  CES-2-1.5-3...............        3  Whirlpool.....................               2  W2H318A-1A.
Cascade............................  CES-2-1.5-4...............        3  Amana.........................               2  ASH130181A.
Cascade............................  CES-2-1.5-4...............        3  Aire-Flo......................               2  2HP13(B,L)18P-1.
Cascade............................  CES-2-1.5-4...............        3  AirPro........................               2  DRHS0181BD.
Cascade............................  CES-2-1.5-4...............        3  American Standard.............               2  2A6B3018A1.
Cascade............................  CES-2-1.5-4...............        3  Bryant........................               2  213ANA018-A.
Cascade............................  CES-2-1.5-4...............        3  Carrier.......................               2  25HBA318A30.
Cascade............................  CES-2-1.5-4...............        3  Coleman.......................               2  DRHS0181BD.
Cascade............................  CES-2-1.5-4...............        3  Ducane........................               2  2HP13(B,L)18P-1.
Cascade............................  CES-2-1.5-4...............        3  Fedders.......................               2  CH18ABD1VF.
Cascade............................  CES-2-1.5-4...............        3  Frigidaire....................               2  FT3BD-018K.
Cascade............................  CES-2-1.5-4...............        3  Gibson........................               2  GT3BD-018K.
Cascade............................  CES-2-1.5-4...............        3  Goodman.......................               2  GSH130181A.
Cascade............................  CES-2-1.5-4...............        3  Lennox........................               2  12HPB18-P.
Cascade............................  CES-2-1.5-4...............        3  Luxaire.......................               2  EABC-F018S.
Cascade............................  CES-2-1.5-4...............        3  Maytag........................               2  DT5BD-018K.
Cascade............................  CES-2-1.5-4...............        3  Rheem.........................               2  13PJA18.
Cascade............................  CES-2-1.5-4...............        3  Ruud..........................               2  UPNE-018JZ.
Cascade............................  CES-2-1.5-4...............        3  Tappan........................               2  FT3BD-018K.
Cascade............................  CES-2-1.5-4...............        3  Trane.........................               2  2TWB3018A1.
Cascade............................  CES-2-1.5-4...............        3  York..........................               2  E1RC018S06.
Cascade............................  CES-2-1.5-4...............        3  Westinghouse..................               2  W2H318A-1A.
Cascade............................  CES-2-1.5-4...............        3  Whirlpool.....................               2  W2H318A-1A.
Cascade............................  CES-2-2-2.................        4  Amana.........................               2  ASH130241A.
Cascade............................  CES-2-2-2.................        4  Aire-Flo......................               2  2HP13(B,L)24P-1.
Cascade............................  CES-2-2-2.................        4  AirPro........................               2  DRHS0241BD.
Cascade............................  CES-2-2-2.................        4  American Standard.............               2  2A6B3024A1.
Cascade............................  CES-2-2-2.................        4  Bryant........................               2  213ANA024-A.
Cascade............................  CES-2-2-2.................        4  Carrier.......................               2  25HBA324A30.
Cascade............................  CES-2-2-2.................        4  Coleman.......................               2  DRHS0241BD.
Cascade............................  CES-2-2-2.................        4  Ducane........................               2  2HP13(B,L)18P-1.
Cascade............................  CES-2-2-2.................        4  Fedders.......................               2  CH24ABD1VF.

[[Page 19898]]

 
Cascade............................  CES-2-2-2.................        4  Frigidaire....................               2  FT3BD-024K.
Cascade............................  CES-2-2-2.................        4  Gibson........................               2  GT3BD-024K.
Cascade............................  CES-2-2-2.................        4  Goodman.......................               2  GSH130241A.
Cascade............................  CES-2-2-2.................        4  Lennox........................               2  12HPB24-P.
Cascade............................  CES-2-2-2.................        4  Luxaire.......................               2  EABC-F024S.
Cascade............................  CES-2-2-2.................        4  Maytag........................               2  DT3BD-024K.
Cascade............................  CES-2-2-2.................        4  Rheem.........................               2  13PJA24.
Cascade............................  CES-2-2-2.................        4  Ruud..........................               2  13PJA24.
Cascade............................  CES-2-2-2.................        4  Tappan........................               2  FT3BD-024K.
Cascade............................  CES-2-2-2.................        4  Trane.........................               2  2TWB3024A1.
Cascade............................  CES-2-2-2.................        4  York..........................               2  E1RC024S06.
Cascade............................  CES-2-2-2.................        4  Westinghouse..................               2  FT3BD-024K.
Cascade............................  CES-2-2-2.................        4  Whirlpool.....................               2  W2H324A-1A.
Cascade............................  CES-2-2-3.................        4  Amana.........................               2  ASH130241A.
Cascade............................  CES-2-2-3.................        4  Aire-Flo......................               2  2HP13(B,L)24P-1.
Cascade............................  CES-2-2-3.................        4  AirPro........................               2  FRHS0241CD.
Cascade............................  CES-2-2-3.................        4  American Standard.............               2  2A6B3024A1.
Cascade............................  CES-2-2-3.................        4  Bryant........................               2  213ANA024-A.
Cascade............................  CES-2-2-3.................        4  Carrier.......................               2  25HBA324A30.
Cascade............................  CES-2-2-3.................        4  Coleman.......................               2  DRHS0241BD.
Cascade............................  CES-2-2-3.................        4  Ducane........................               2  2HP13(B,L)18P-1.
Cascade............................  CES-2-2-3.................        4  Fedders.......................               2  CH24ABD1VF.
Cascade............................  CES-2-2-3.................        4  Frigidaire....................               2  FT3BD-024K.
Cascade............................  CES-2-2-3.................        4  Gibson........................               2  GT3BD-024K.
Cascade............................  CES-2-2-3.................        4  Goodman.......................               2  GSH130241A.
Cascade............................  CES-2-2-3.................        4  Lennox........................               2  12HPB24-P.
Cascade............................  CES-2-2-3.................        4  Luxaire.......................               2  EABC-F024S.
Cascade............................  CES-2-2-3.................        4  Maytag........................               2  DT3BD-024K.
Cascade............................  CES-2-2-3.................        4  Rheem.........................               2  13PJA24.
Cascade............................  CES-2-2-3.................        4  Ruud..........................               2  13PJA24.
Cascade............................  CES-2-2-3.................        4  Tappan........................               2  FT3BD-024K.
Cascade............................  CES-2-2-3.................        4  Trane.........................               2  2TWB3024A1.
Cascade............................  CES-2-2-3.................        4  York..........................               2  E1RC024S06.
Cascade............................  CES-2-2-3.................        4  Westinghouse..................               2  FT3BD-024K.
Cascade............................  CES-2-2-3.................        4  Whirlpool.....................               2  W2H324A-1A.
Cascade............................  CES-2-2-4.................        4  Amana.........................               2  ASH130241A.
Cascade............................  CES-2-2-4.................        4  Aire-Flo......................               2  2HP13(B,L)24P-1.
Cascade............................  CES-2-2-4.................        4  AirPro........................               2  FRHS0241CD.
Cascade............................  CES-2-2-4.................        4  American Standard.............               2  2A6B3024A1.
Cascade............................  CES-2-2-4.................        4  Bryant........................               2  213ANA024-A.
Cascade............................  CES-2-2-4.................        4  Carrier.......................               2  25HBA324A30.
Cascade............................  CES-2-2-4.................        4  Coleman.......................               2  DRHS0241BD.
Cascade............................  CES-2-2-4.................        4  Ducane........................               2  2HP13(B,L)18P-1.
Cascade............................  CES-2-2-4.................        4  Fedders.......................               2  CH24ABD1VF.
Cascade............................  CES-2-2-4.................        4  Frigidaire....................               2  FT3BD-024K.
Cascade............................  CES-2-2-4.................        4  Gibson........................               2  GT3BD-024K.
Cascade............................  CES-2-2-4.................        4  Goodman.......................               2  GSH130241A.
Cascade............................  CES-2-2-4.................        4  Lennox........................               2  12HPB24-P.
Cascade............................  CES-2-2-4.................        4  Luxaire.......................               2  EABC-F024S.
Cascade............................  CES-2-2-4.................        4  Maytag........................               2  DT3BD-024K.
Cascade............................  CES-2-2-4.................        4  Rheem.........................               2  13PJA24.
Cascade............................  CES-2-2-4.................        4  Ruud..........................               2  13PJA24.
Cascade............................  CES-2-2-4.................        4  Tappan........................               2  FT3BD-024K.
Cascade............................  CES-2-2-4.................        4  Trane.........................               2  2TWB3024A1.
Cascade............................  CES-2-2-4.................        4  York..........................               2  E1RC024S06.
Cascade............................  CES-2-2-4.................        4  Westinghouse..................               2  FT3BD-024K.
Cascade............................  CES-2-2-4.................        4  Whirlpool.....................               2  W2H324A-1A.
Cascade............................  CES-2-2-5.................        4  Amana.........................               2  ASH130241A.
Cascade............................  CES-2-2-5.................        4  Aire-Flo......................               2  2HP13(B,L)24P-1.
Cascade............................  CES-2-2-5.................        4  AirPro........................               2  FRHS0241CD.
Cascade............................  CES-2-2-5.................        4  American Standard.............               2  2A6B3024A1.
Cascade............................  CES-2-2-5.................        4  Bryant........................               2  213ANA024-A.
Cascade............................  CES-2-2-5.................        4  Carrier.......................               2  25HBA324A30.
Cascade............................  CES-2-2-5.................        4  Coleman.......................               2  DRHS0241BD.
Cascade............................  CES-2-2-5.................        4  Ducane........................               2  2HP13(B,L)24P-1.
Cascade............................  CES-2-2-5.................        4  Fedders.......................               2  CH24ABD1VF.
Cascade............................  CES-2-2-5.................        4  Frigidaire....................               2  FT3BD-024K.
Cascade............................  CES-2-2-5.................        4  Gibson........................               2  GT3BD-024K.

[[Page 19899]]

 
Cascade............................  CES-2-2-5.................        4  Goodman.......................               2  GSH130241A.
Cascade............................  CES-2-2-5.................        4  Lennox........................               2  12HPB24-P.
Cascade............................  CES-2-2-5.................        4  Luxaire.......................               2  EABC-F024S.
Cascade............................  CES-2-2-5.................        4  Maytag........................               2  DT3BD-024K.
Cascade............................  CES-2-2-5.................        4  Rheem.........................               2  13PJA24.
Cascade............................  CES-2-2-5.................        4  Ruud..........................               2  13PJA24.
Cascade............................  CES-2-2-5.................        4  Tappan........................               2  FT3BD-024K.
Cascade............................  CES-2-2-5.................        4  Trane.........................               2  2TWB3024A1.
Cascade............................  CES-2-2-5.................        4  York..........................               2  E1RC024S06.
Cascade............................  CES-2-2-5.................        4  Westinghouse..................               2  FT3BD-024K.
Cascade............................  CES-2-2-5.................        4  Whirlpool.....................               2  W2H324A-1A.
Cascade............................  CES-2-2-6.................        4  Amana.........................               2  ASH130241A.
Cascade............................  CES-2-2-6.................        4  Aire-Flo......................               2  2HP13(B,L)24P-1.
Cascade............................  CES-2-2-6.................        4  AirPro........................               2  FRHS0241CD.
Cascade............................  CES-2-2-6.................        4  American Standard.............               2  2A6B3024A1.
Cascade............................  CES-2-2-6.................        4  Bryant........................               2  213ANA024-A.
Cascade............................  CES-2-2-6.................        4  Carrier.......................               2  25HBA324A30.
Cascade............................  CES-2-2-6.................        4  Coleman.......................               2  DRHS0241BD.
Cascade............................  CES-2-2-6.................        4  Ducane........................               2  2HP13(B,L)24P-1.
Cascade............................  CES-2-2-6.................        4  Fedders.......................               2  CH24ABD1VF.
Cascade............................  CES-2-2-6.................        4  Frigidaire....................               2  FT3BD-024K.
Cascade............................  CES-2-2-6.................        4  Gibson........................               2  GT3BD-024K.
Cascade............................  CES-2-2-6.................        4  Goodman.......................               2  GSH130241A.
Cascade............................  CES-2-2-6.................        4  Lennox........................               2  12HPB24-P.
Cascade............................  CES-2-2-6.................        4  Luxaire.......................               2  EABC-F024S.
Cascade............................  CES-2-2-6.................        4  Maytag........................               2  DT3BD-024K.
Cascade............................  CES-2-2-6.................        4  Rheem.........................               2  13PJA24.
Cascade............................  CES-2-2-6.................        4  Ruud..........................               2  13PJA24.
Cascade............................  CES-2-2-6.................        4  Tappan........................               2  FT3BD-024K.
Cascade............................  CES-2-2-6.................        4  Trane.........................               2  2TWB3024A1.
Cascade............................  CES-2-2-6.................        4  York..........................               2  E1RC024S06.
Cascade............................  CES-2-2-6.................        4  Westinghouse..................               2  FT3BD-024K.
Cascade............................  CES-2-2-6.................        4  Whirlpool.....................               2  W2H324A-1A.
Cascade............................  CES-2-2-7.................        4  Amana.........................               2  ASH130241A.
Cascade............................  CES-2-2-7.................        4  Aire-Flo......................               2  2HP13(B,L)24P-1.
Cascade............................  CES-2-2-7.................        4  AirPro........................               2  FRHS0241CD.
Cascade............................  CES-2-2-7.................        4  American Standard.............               2  2A6B3024A1.
Cascade............................  CES-2-2-7.................        4  Bryant........................               2  213ANA024-A.
Cascade............................  CES-2-2-7.................        4  Carrier.......................               2  25HBA324A30.
Cascade............................  CES-2-2-7.................        4  Coleman.......................               2  DRHS0241BD.
Cascade............................  CES-2-2-7.................        4  Ducane........................               2  2HP13(B,L)24P-1.
Cascade............................  CES-2-2-7.................        4  Fedders.......................               2  CH24ABD1VF.
Cascade............................  CES-2-2-7.................        4  Frigidaire....................               2  FT3BD-024K.
Cascade............................  CES-2-2-7.................        4  Gibson........................               2  GT3BD-024K.
Cascade............................  CES-2-2-7.................        4  Goodman.......................               2  GSH130241A.
Cascade............................  CES-2-2-7.................        4  Lennox........................               2  12HPB24-P.
Cascade............................  CES-2-2-7.................        4  Luxaire.......................               2  EABC-F024S.
Cascade............................  CES-2-2-7.................        4  Maytag........................               2  DT3BD-024K.
Cascade............................  CES-2-2-7.................        4  Rheem.........................               2  13PJA24.
Cascade............................  CES-2-2-7.................        4  Ruud..........................               2  13PJA24.
Cascade............................  CES-2-2-7.................        4  Tappan........................               2  FT3BD-024K.
Cascade............................  CES-2-2-7.................        4  Trane.........................               2  2TWB3024A1.
Cascade............................  CES-2-2-7.................        4  York..........................               2  E1RC024S06.
Cascade............................  CES-2-2-7.................        4  Westinghouse..................               2  FT3BD-024K.
Cascade............................  CES-2-2-7.................        4  Whirlpool.....................               2  W2H324A-1A.
Cascade............................  CES-2-2-8.................        4  Amana.........................               2  ASH130241A.
Cascade............................  CES-2-2-8.................        4  Aire-Flo......................               2  2HP13(B,L)24P-1.
Cascade............................  CES-2-2-8.................        4  AirPro........................               2  FRHS0241CD.
Cascade............................  CES-2-2-8.................        4  American Standard.............               2  2A6B3024A1.
Cascade............................  CES-2-2-8.................        4  Bryant........................               2  213ANA024-A.
Cascade............................  CES-2-2-8.................        4  Carrier.......................               2  25HBA324A30.
Cascade............................  CES-2-2-8.................        4  Coleman.......................               2  DRHS0241BD.
Cascade............................  CES-2-2-8.................        4  Ducane........................               2  2HP13(B,L)24P-1.
Cascade............................  CES-2-2-8.................        4  Fedders.......................               2  CH24ABD1VF.
Cascade............................  CES-2-2-8.................        4  Frigidaire....................               2  FT3BD-024K.
Cascade............................  CES-2-2-8.................        4  Gibson........................               2  GT3BD-024K.
Cascade............................  CES-2-2-8.................        4  Goodman.......................               2  GSH130241A.
Cascade............................  CES-2-2-8.................        4  Lennox........................               2  12HPB24-P.

[[Page 19900]]

 
Cascade............................  CES-2-2-8.................        4  Luxaire.......................               2  EABC-F024S.
Cascade............................  CES-2-2-8.................        4  Maytag........................               2  DT3BD-024K.
Cascade............................  CES-2-2-8.................        4  Rheem.........................               2  13PJA24.
Cascade............................  CES-2-2-8.................        4  Ruud..........................               2  13PJA24.
Cascade............................  CES-2-2-8.................        4  Tappan........................               2  FT3BD-024K.
Cascade............................  CES-2-2-8.................        4  Trane.........................               2  2TWB3024A1.
Cascade............................  CES-2-2-8.................        4  York..........................               2  E1RC024S06.
Cascade............................  CES-2-2-8.................        4  Westinghouse..................               2  FT3BD-024K.
Cascade............................  CES-2-2-8.................        4  Whirlpool.....................               2  W2H324A-1A.
Cascade............................  CES-2-2.5-4...............        5  Amana.........................               2  ASH130301A.
Cascade............................  CES-2-2.5-4...............        5  Aire-Flo......................               2  2HP13(B,L)30P-1.
Cascade............................  CES-2-2.5-4...............        5  AirPro........................               2  FRHS0301CD.
Cascade............................  CES-2-2.5-4...............        5  American Standard.............               2  2A6B3030A1.
Cascade............................  CES-2-2.5-4...............        5  Bryant........................               2  213ANA030-A.
Cascade............................  CES-2-2.5-4...............        5  Carrier.......................               2  25HBA330A30.
Cascade............................  CES-2-2.5-4...............        5  Coleman.......................               2  DRHS0301BD.
Cascade............................  CES-2-2.5-4...............        5  Ducane........................               2  2HP13(B,L)30P-1.
Cascade............................  CES-2-2.5-4...............        5  Fedders.......................               2  CH30ABD1VF.
Cascade............................  CES-2-2.5-4...............        5  Frigidaire....................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-4...............        5  Gibson........................               2  GT3BD-030K.
Cascade............................  CES-2-2.5-4...............        5  Goodman.......................               2  CPLT30-1.
Cascade............................  CES-2-2.5-4...............        5  Lennox........................               2  12HPB30-P.
Cascade............................  CES-2-2.5-4...............        5  Luxaire.......................               2  EABC-F030S.
Cascade............................  CES-2-2.5-4...............        5  Maytag........................               2  DT3BD-030K.
Cascade............................  CES-2-2.5-4...............        5  Rheem.........................               2  13PJA30.
Cascade............................  CES-2-2.5-4...............        5  Ruud..........................               2  13PJA30.
Cascade............................  CES-2-2.5-4...............        5  Tappan........................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-4...............        5  Trane.........................               2  2TWB3030A1.
Cascade............................  CES-2-2.5-4...............        5  York..........................               2  E1RC030S06.
Cascade............................  CES-2-2.5-4...............        5  Westinghouse..................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-4...............        5  Whirlpool.....................               2  WGH430A.
Cascade............................  CES-2-2.5-5...............        5  Amana.........................               2  ASH130301A.
Cascade............................  CES-2-2.5-5...............        5  Aire-Flo......................               2  2HP13(B,L)30P-1.
Cascade............................  CES-2-2.5-5...............        5  AirPro........................               2  FRHS0301CD.
Cascade............................  CES-2-2.5-5...............        5  American Standard.............               2  2A6B3030A1.
Cascade............................  CES-2-2.5-5...............        5  Bryant........................               2  213ANA030-A.
Cascade............................  CES-2-2.5-5...............        5  Carrier.......................               2  25HBA330A30.
Cascade............................  CES-2-2.5-5...............        5  Coleman.......................               2  DRHS0301BD.
Cascade............................  CES-2-2.5-5...............        5  Ducane........................               2  2HP13(B,L)30P-1.
Cascade............................  CES-2-2.5-5...............        5  Fedders.......................               2  CH30ABD1VF.
Cascade............................  CES-2-2.5-5...............        5  Frigidaire....................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-5...............        5  Gibson........................               2  GT3BD-030K.
Cascade............................  CES-2-2.5-5...............        5  Goodman.......................               2  CPLT30-1.
Cascade............................  CES-2-2.5-5...............        5  Lennox........................               2  12HPB30-P.
Cascade............................  CES-2-2.5-5...............        5  Luxaire.......................               2  EABC-F030S.
Cascade............................  CES-2-2.5-5...............        5  Maytag........................               2  DT3BD-030K.
Cascade............................  CES-2-2.5-5...............        5  Rheem.........................               2  13PJA30.
Cascade............................  CES-2-2.5-5...............        5  Ruud..........................               2  13PJA30.
Cascade............................  CES-2-2.5-5...............        5  Tappan........................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-5...............        5  Trane.........................               2  2TWB3030A1.
Cascade............................  CES-2-2.5-5...............        5  York..........................               2  E1RC030S06.
Cascade............................  CES-2-2.5-5...............        5  Westinghouse..................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-5...............        5  Whirlpool.....................               2  WGH430A.
Cascade............................  CES-2-2.5-6...............        5  Amana.........................               2  ASH130301A.
Cascade............................  CES-2-2.5-6...............        5  Aire-Flo......................               2  2HP13(B,L)30P-1.
Cascade............................  CES-2-2.5-6...............        5  AirPro........................               2  FRHS0301CD.
Cascade............................  CES-2-2.5-6...............        5  American Standard.............               2  2A6B3030A1.
Cascade............................  CES-2-2.5-6...............        5  Bryant........................               2  213ANA030-A.
Cascade............................  CES-2-2.5-6...............        5  Carrier.......................               2  25HBA330A30.
Cascade............................  CES-2-2.5-6...............        5  Coleman.......................               2  DRHS0301BD.
Cascade............................  CES-2-2.5-6...............        5  Ducane........................               2  2HP13(B,L)30P-1.
Cascade............................  CES-2-2.5-6...............        5  Fedders.......................               2  CH30ABD1VF.
Cascade............................  CES-2-2.5-6...............        5  Frigidaire....................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-6...............        5  Gibson........................               2  GT3BD-030K.
Cascade............................  CES-2-2.5-6...............        5  Goodman.......................               2  CPLT30-1.
Cascade............................  CES-2-2.5-6...............        5  Lennox........................               2  12HPB30-P.
Cascade............................  CES-2-2.5-6...............        5  Luxaire.......................               2  EABC-F030S.
Cascade............................  CES-2-2.5-6...............        5  Maytag........................               2  DT3BD-030K.

[[Page 19901]]

 
Cascade............................  CES-2-2.5-6...............        5  Rheem.........................               2  13PJA30.
Cascade............................  CES-2-2.5-6...............        5  Ruud..........................               2  13PJA30.
Cascade............................  CES-2-2.5-6...............        5  Tappan........................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-6...............        5  Trane.........................               2  2TWB3030A1.
Cascade............................  CES-2-2.5-6...............        5  York..........................               2  E1RC030S06.
Cascade............................  CES-2-2.5-6...............        5  Westinghouse..................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-6...............        5  Whirlpool.....................               2  WGH430A.
Cascade............................  CES-2-2.5-7...............        5  Amana.........................               2  ASH130301A.
Cascade............................  CES-2-2.5-7...............        5  Aire-Flo......................               2  2HP13(B,L)30P-1.
Cascade............................  CES-2-2.5-7...............        5  AirPro........................               2  FRHS0301CD.
Cascade............................  CES-2-2.5-7...............        5  American Standard.............               2  2A6B3030A1.
Cascade............................  CES-2-2.5-7...............        5  Bryant........................               2  213ANA030-A.
Cascade............................  CES-2-2.5-7...............        5  Carrier.......................               2  25HBA330A30.
Cascade............................  CES-2-2.5-7...............        5  Coleman.......................               2  DRHS0301BD.
Cascade............................  CES-2-2.5-7...............        5  Ducane........................               2  2HP13(B,L)30P-1.
Cascade............................  CES-2-2.5-7...............        5  Fedders.......................               2  CH30ABD1VF.
Cascade............................  CES-2-2.5-7...............        5  Frigidaire....................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-7...............        5  Gibson........................               2  GT3BD-030K.
Cascade............................  CES-2-2.5-7...............        5  Goodman.......................               2  CPLT30-1.
Cascade............................  CES-2-2.5-7...............        5  Lennox........................               2  12HPB30-P.
Cascade............................  CES-2-2.5-7...............        5  Luxaire.......................               2  EABC-F030S.
Cascade............................  CES-2-2.5-7...............        5  Maytag........................               2  DT3BD-030K.
Cascade............................  CES-2-2.5-7...............        5  Rheem.........................               2  13PJA30.
Cascade............................  CES-2-2.5-7...............        5  Ruud..........................               2  13PJA30.
Cascade............................  CES-2-2.5-7...............        5  Tappan........................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-7...............        5  Trane.........................               2  2TWB3030A1.
Cascade............................  CES-2-2.5-7...............        5  York..........................               2  E1RC030S06.
Cascade............................  CES-2-2.5-7...............        5  Westinghouse..................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-7...............        5  Whirlpool.....................               2  WGH430A.
Cascade............................  CES-2-2.5-8...............        5  Amana.........................               2  ASH130301A.
Cascade............................  CES-2-2.5-8...............        5  Aire-Flo......................               2  2HP13(B,L)30P-1.
Cascade............................  CES-2-2.5-8...............        5  AirPro........................               2  FRHS0301CD.
Cascade............................  CES-2-2.5-8...............        5  American Standard.............               2  2A6B3030A1.
Cascade............................  CES-2-2.5-8...............        5  Bryant........................               2  213ANA030-A.
Cascade............................  CES-2-2.5-8...............        5  Carrier.......................               2  25HBA330A30.
Cascade............................  CES-2-2.5-8...............        5  Coleman.......................               2  DRHS0301BD.
Cascade............................  CES-2-2.5-8...............        5  Ducane........................               2  2HP13(B,L)30P-1.
Cascade............................  CES-2-2.5-8...............        5  Fedders.......................               2  CH30ABD1VF.
Cascade............................  CES-2-2.5-8...............        5  Frigidaire....................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-8...............        5  Gibson........................               2  GT3BD-030K.
Cascade............................  CES-2-2.5-8...............        5  Goodman.......................               2  CPLT30-1.
Cascade............................  CES-2-2.5-8...............        5  Lennox........................               2  12HPB30-P.
Cascade............................  CES-2-2.5-8...............        5  Luxaire.......................               2  EABC-F030S.
Cascade............................  CES-2-2.5-8...............        5  Maytag........................               2  DT3BD-030K.
Cascade............................  CES-2-2.5-8...............        5  Rheem.........................               2  13PJA30.
Cascade............................  CES-2-2.5-8...............        5  Ruud..........................               2  13PJA30.
Cascade............................  CES-2-2.5-8...............        5  Tappan........................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-8...............        5  Trane.........................               2  2TWB3030A1.
Cascade............................  CES-2-2.5-8...............        5  York..........................               2  E1RC030S06.
Cascade............................  CES-2-2.5-8...............        5  Westinghouse..................               2  FT3BD-030K.
Cascade............................  CES-2-2.5-8...............        5  Whirlpool.....................               2  WGH430A.
--------------------------------------------------------------------------------------------------------------------------------------------------------

Design Characteristics Constituting the Grounds for Petition

    The United States Department of Energy has designated the American 
Refrigeration Institute (ARI) as the body of air conditioning industry 
partners to develop and maintain standards for compliance to the 
National Appliance Energy Conservation Act of 1987 (NAECA). (10 CFR 
430). The two standards that were developed by ARI that are applicable 
to the CES are the ARI 210/240 and ARI 340/360.
    ARI 210/240 is the standard that certifies the performance of units 
that are 65,000 Btu/hr or less. Currently, this standard requires that 
a split system heat pump meet a minimum SEER of 10. The standard also 
stipulates that it meet the maximum standard airflow rate of 37.5 CFM/
1000Btu/hr. This CFM is assumed to be applicable to the indoor unit 
that has only one blower-motor. The CES unit does not fit this model in 
that the indoor blower-motor combinations can range from 2 to 8 indoor 
blower-motors that are independently operating. Thus a waiver is sought 
since the current procedures for testing do not apply.
    This request for a waiver will include SEER calculations that are 
the result of live data for a multi-indoor blower-motor configuration, 
those specific procedures followed during the test, the data in the 
test were conducted by the Texas A&M University Energy Services

[[Page 19902]]

Laboratory (TAMU-ESL) by Michael Davis under the supervision of Dr. 
Dennis O'Neal, Dean of Mechanical Engineering, Texas A&M University.
    The following results show that under ARI 210/240 conditions, 
connecting the CES 5ton-8 zone unit to an Amana RHF030 heat pump with 
an SEER of 12-14 (dependant on the indoor blower-coil for the rating) 
produced an SEER value based on the calculations of 18.1 and an HSPF of 
9.5. This is a 29% savings on cooling Seasonal energy efficiency Ratio 
and a 19% increase over the heating seasonal efficiency ratio.
    The ``Results of Heating and Cooling Performance Testing of Cascade 
Energy Saver<SUP>TM</SUP>'' report from Texas A&M is attached in the 
Appendix A.

Specific Requirements Sought To Be Waived

    Cascade requests a waiver by this petition from the procedures of 
ARI210/240 for models that are 65000Btu/h and smaller because the 
Cascade Manufacturing indoor blower coil models have more than one 
blower per coil and up to and as many as eight blowers. Thus, it does 
not conform to the test procedures of ARI 210/240, which are based 
solely on one single indoor-coil blower. We have proven with laboratory 
tests that an enhanced multi-blower fan coil is efficient and that by 
slight modifications to the current ARI 210/240 procedures, Cascade 
Energy Saver units can be tested and the results will show that the 
SEER and HSPF are easily measurable.
    Pursuant to the purchase of the CES, Cascade seeks to be a viable 
and profitable business concern and therefor desires to implement its 
business plan for manufacturing and distribution of mass quantities of 
the CES units in the various models and sizes to the general public 
within the United States. To effectuate the manufacturing and 
distribution, Cascade has entered into certain agreements with United 
Chester Industries, Inc. dba United Mechanical, Inc., an existing 
mechanical contractor with manufacturing and distribution capabilities.
    Cascade seeks immediate relief through this waiver to avert undo 
economic hardship.

Discussion in Details for the Requested Waiver

    Concerning ARI 210/240
    1. The ARI 210/240 test procedure does not take into account indoor 
blower coils with more than one indoor blower and motor. The Cascade 
Energy Saver indoor coil-blower is thus a deviation from the ARI 210/
240 model. This design is what Cascade believes will be product to fill 
a market niche and that the consumer with find huge energy saving 
benefits.
    Cascade contracted with TAMU-ESL to perform the ARI 210/240 testing 
comprised of two operating conditions, namely with 2 variations/
combinations of indoor blowers and outdoor heat pumps, in order to 
demonstrate that the efficiencies are within the acceptable values of 
the NAECA, namely, SEER, COP, HSPF.
    2. In addition to the data, the assumptions, the test conditions, 
the procedures followed by TAMU-ESL are all included in the report from 
TAMU-ESL.
    3. These procedures are the means by which the Cascade CES units 
will meet the standards as set forth by the NEACA of 1987. Once 
reviewed by DOE or its assigns, we assert that the test procedures 
presented herein can be incorporated into the ARI 210/240 as an 
approved manner to test multi-blower coil assemblies like the Cascade 
Energy Saver.
    4. It is Cascade's intention to cooperate with DOE or its assigns, 
in rigorously supporting the data presented herein, the procedure as 
detailed by TAMU-ESL, our laboratory, the efficiencies reported and the 
conclusions.
    5. Cascade Manufacturing believes that the benefits to the consumer 
in the future usage of this CES unit will be dramatic in terms of 
reducing energy consumption which is the intent of the NAECA.

Identification of Manufacturers With Similar Design Characteristics

    There are no other known manufacturers or products that are like 
the CES. This is the patented feature of the CES. The fact that the CES 
using multiple blowers is what creates the problem with the standards 
as noted previously in this Petition.

Alternative Test Procedures To Evaluate Energy Consumption 
Characteristics

    <bullet> Cascade Manufacturing entered into a testing contract with 
Texas A&M University's Energy Services Laboratory. The procedure that 
TAMU-ESL followed was the ARI 210/240 procedure. TAMU-ESL ``modeled'' 
the Cascade system as a 2 speed blower and the compressors with 2 
stages.
    <bullet> Thus, TAMU-ESL's procedure was to collect data under the 
Tests A,B,C and D with all 8 blowers running (modeled as a single 
blower) and both compressors running (modeled as a single 2 speed 
compressor) and this is a full load case. Then, part load conditions 
were 4 blowers operating (modeled as a low speed single fan) and one 
compressor operating (modeled as a single compressor in low speed).
    <bullet> The CES unit had a 5 ton evaporator coil, split 50%/50% in 
the sense that it has a 4 row slab coil with 2 of the rows being 
connected to one 2.5 ton heat pump and the other two rows connected to 
the other 2.5 ton heat pump. The slab coil is patented in its design. 
It is a face split. Rows 1 and 3 are connected to one heat pump and 
rows 2 and 4 are connected to the other heat pump. The coil surface 
stays wet with one or both of the heat pumps operating.
    <bullet> When the full load test was conducted, all 8 fans were on. 
The 8 fans are powered by individual \1/3\hp GE ECM motors which use 50 
watts of power each, thus 400 watts total for all 8 fans. Each fan was 
set to blow only 250 cfm at 0.5'' ESP, for a total of 2000 cfm (i.e., 5 
tons of air). The outlet from each of the 8 zones was ducted with flex 
into a single 16'' header. The 16'' header was then ducted into the 
wind tunnel.
    <bullet> During the part load test, only four zone blowers were 
operating. Each of these four blowers was delivering 250 cfm at 0.5''; 
ESP, for a total of 1000 cfm which is the 400 cfm per ton for 2.5 tons. 
The ducting was the same as in full load.
    <bullet> Tests A,B and C were run in accordance with the ARI210/240 
procedure and pursuant to the notes summarized above. Test D was not 
run since we chose to use the default coefficient of degradation of 
0.25.
    <bullet> Finally, it is evident to me from these results that the 
ARI 210/240 procedures worked for the Cascade unit. Further, the 
procedure can and should be evaluated by the industry bodies that are 
responsible for code enforcement to implement changes accordingly to 
allow for testing of Cascade units.

Petitioner

Gary R. Scoggins, P.E.,

Special Projects Engineer.

Representative for Cascade Group, LLC general partner for Cascade 
Manufacturing LP.
2183 Buckingham Road <greek-i>301,
Richardson, Texas 75081-5499
1-214-341-9300
Patents 5,701,750 and 6,792,768

Appendix A--The Test Report From Texas A&M University, College Station, 
Texas, Dated August 27, 2004

Results of Heating and Cooling Performance Testing of Cascade Energy 
Saver<SUP>TM</SUP>

Final Report

Submitted to

Cascade Manufacturing, LP, c/o United Mechanical, Inc., 11540 Plano 
Road, Dallas, Texas 75243.


[[Page 19903]]


Submitted by

Michael A. Davis, Assistant Research Engineer;
Carlos Ortiz, P.E., Assistant Research Engineer;
August 27, 2004.

Energy Systems Laboratory, Texas Engineering Experiment Station, 
College Station, Texas 77843.

Executive Summary

    Cascade Manufacturing, LP (CM) contracted with the Energy 
Systems Laboratory (ESL) to conduct heating and cooling rating and 
performance tests on their multizoned coil blower unit called, 
``Cascade Energy Saver'' (CES) in accordance with the ARI Standard 
for Air Source Split system heat pumps. The equipment tested 
consisted of one CES unit with 8 blowers, one Aspen 5 ton Coil model 
<greek-i> BHA40 60+x3 50/50SP (a two circuit slab coil with TXVs, 
2.5 tons per circuit), and two Amana 2.5 ton Heat pump model RHF 
030--12 SEER.
    At the time that this report was written and the tests were 
conducted, the ARI 210/240 (Standard) was not clear with a procedure 
for the proper rating and performance tests for an HRCU-A-CB with 
multiple-zone blowers as manufactured by CM. In order to obtain 
laboratory data that would support an SEER, HSPF, COP and EER 
determination, ESL determined to follow and apply the Standard's 
HRCU-A-CB as closely as possible (exceptions, deviations and 
assumptions to follow in this document). It appeared to ESL 
engineers that the Standard could be applied to the performance 
ratings of a CES unit when fixed indoor blower fan speeds were used 
in combination with (1.) traditional 400 cfm per ton and (2.) 
various compressor combinations. Before describing the application 
of the Standard, a description of the CES unit will be given in 
order for the reader to understand the logic behind the application 
of the Standard.
    The CES unit consists of two heat pump units connected to an 
evaporator that has two refrigerant circuits. The evaporator is 
followed by a plenum which houses multiple blowers that are 
independently operated by a control system developed specifically 
for the blower/evaporator/heat pump system. When in normal 
operation, the control system manages the operation of the 
compressors and fans in order to meet the system load as dictated by 
the multiple thermostats connected to the controller. The blower 
motors are variable speed motors manufactured by GE, model 2.3 ECM 
that can be operated at full capacity during peak operation or 
scaled back to lower rotational speeds at part load conditions. With 
the lower rotational speeds, lower cfm rates can be delivered 
independently to each zone connected to the system.
    The heat pump condenser units are off-the-shelf units and are 
not manufactured by Cascade Manufacturing, rather their design 
permits the use of any manufactured unit from companies such as 
Amana Trane, Carrier, Lennox, or others. For our tests, we were 
supplied with Amana Heat Pumps. The heat pumps were operated in 
either an on or off mode and each one had single speed compressors 
and single speed fans. The fact that there are two heat pumps of 
equal size providing the two stages of cooling and heating with up 
to 8 indoor fans in a draw thru configuration to the dual circuit 
evaporator coil was the primary reason for selecting the specific 
guidelines from the Standard. The Standard gives detailed 
instructions for a variety of compressor operation combinations but 
it does not adequately describe various combinations of indoor 
fan(s) and two evaporator/compressor combinations possible with this 
unit. It was decided that the standard descriptions where the title 
included ``units with two-speed compressors, two compressors, or 
cylinder unloading'' most closely matched the operation of the CES 
unit. Typically units with two compressors also have separate 
refrigerant circuits on both the indoor and outdoor coils which 
match the configuration of the CES unit.
    The two major differences with this system in light of the 
Standard was how to apply the Standard to (1.) a coil blower unit 
with a 4 row, dual circuited evaporator coil which is circuited with 
full face of the 1st and 3rd rows on one heat pump and rows 2 and 4 
on the second heat pump, (2.) more than one evaporator blower. The 
coil blower unit tested had 8 blowers. The Standard does not 
describe how to handle the various air flows that can be produced 
with eight blowers. It was determined that the best way to test the 
unit was to apply full-load air flows as determined by nominal 400 
cfm per ton (compressor) operation. For example, if both 2.5 ton 
heat pumps were operating, the rated air flow that was tested was 
2,000 cfm. With one heat pump running, the coil blower unit would 
have half the heating/cooling capacity therefore the full load air 
flow would be 1,000 cfm which is half of the two heat pump supply 
side air flow. This interpretation of the Standard was used for both 
heating and cooling tests.
    For cooling, testing was done following the guidelines in ARI 
210/240 section A2.1.3. Tests A, B, and C were conducted for both 
single heat pump and two heat pump operation. Test D was not done 
and the default C<INF>D</INF> of 0.25 was used for SEER 
calculations. The indoor air-enthalpy method was used during the 
tests. A description of the test facilities and the energy balance 
method is included below. Proper energy balances were achieved for 
all tests as were within the specifications of the standard. The 
results of the cooling tests are included in the table below.
    For heating, testing was done following the guidelines in ARI 
210/240 section A2.2.2. Tests were conducted at 62F (one heat pump), 
47F (one and two heat pumps), 35F (one and two heat pumps), and 17F 
(two heat pumps). The indoor air-enthalpy method was used during the 
tests. Proper energy balances were achieved on all test except the 
17F test. Due to the cycling of the heat pumps between heating and 
defrost, two phase transients in the refrigerant circuit prevented a 
good measurement of the refrigerant flow until the unit reached 
steady state. The period of time where the refrigerant was in two 
phases was sufficient to prevent a proper energy balance from being 
achieved. The air-side measurements were taken with the same 
instrumentation during the 17F tests as were used during all other 
testing. It is reasonable to assume the air side measurements were 
accurate during the 17F tests since proper energy balances were 
achieved during all other tests. The results of the heating tests 
are included in the table below.

----------------------------------------------------------------------------------------------------------------
                                                                                    Total power
                                                      Total capacity (btuh)            (kW)             EER
----------------------------------------------------------------------------------------------------------------
                                                     Cooling
----------------------------------------------------------------------------------------------------------------
A.............................................  65,201..........................             4.4            14.8
B.............................................  63,766..........................             3.8            16.6
C.............................................  58,393..........................             3.9            15.0
SEER..........................................  18.1............................  ..............  ..............
----------------------------------------------------------------------------------------------------------------
                                                Total capacity..................     Total power             COP
                                                (btuh)..........................            (kW)
----------------------------------------------------------------------------------------------------------------
                                                     Heating
----------------------------------------------------------------------------------------------------------------
62F...........................................  37,979 (1 comp).................             3.1             3.6
47F...........................................  67,827..........................             5.7             3.5
35F...........................................  56,561..........................             5.2             3.2
17F...........................................  37,645..........................             4.5             2.5
HSPF..........................................  9.5.............................  ..............  ..............
----------------------------------------------------------------------------------------------------------------


[[Page 19904]]

Facilities and Procedure

    All of the tests were conducted in the psychrometric rooms at 
the Energy Systems Laboratory which is part of the Texas Engineering 
Experiment Station a division within the Texas A&M University 
System. These rooms were completed in 1986 and have been used for 
research projects and industry testing. The rooms were designed for 
testing of systems with cooling capacities up to 10 tons. Chilled 
water is provided to the rooms by a 75 ton Trane screw chiller. 
Reheat is provided by 40 kW of electrical strip heaters in the 
conditioning ductwork. In addition, a desiccant system is used to 
provide low humidity conditions in either room. The psychrometric 
rooms allow indoor and outdoor dry-bulb and wet-bulb temperatures to 
be maintained within approximately <plus-minus> 0.3 [deg]C (0.5 
[deg]F) during steady state operations. Temperatures from 17 [deg]F 
to 120 [deg]F have been maintained for tests in the rooms for 
previous tests. The rooms are capable of running all standard ARI 
210/240 (ARI 2003) and ASHRAE 37/116 (ASHRAE 1988 and 1983) unitary 
heat pump and air conditioners tests, which include both heating and 
cooling mode.
    Electric resistance heaters and chilled water coils are used to 
maintain room temperature. Reheat in each room is provided by four 
banks of 9.9 kW electrical strip heaters in the conditioning 
ductwork. The cooling coil is supplied with a water ethylene glycol 
solution from the chiller. A 1000 gallon water storage tank is 
mounted in the system to stabilize the chilled water temperature and 
reduce the cycling of the chiller. Steam from an electric-fired 
boiler and dehumidification coils control the humidity in the rooms. 
The dehumidification coils are fed from the same cool storage tank 
as the cooling coils. The boiler supplies steam directly into the 
supply air duct. Room temperature is maintained by adjusting the 
chilled water flow to coils with VSD driven pumps in combination 
with the operation of the reheat coils.
    The indoor test section includes the indoor air flow chamber and 
the indoor fan coil section. The air flow chamber fan draws 
conditioned air from the indoor room through the indoor test 
section. An adjustable damper is used to maintain the amount of air 
flow specified for each unit. After leaving the air flow chamber, 
conditioned air is routed back into the indoor room. Figure 1 shows 
a sketch of the indoor and outdoor rooms as used for these tests.
    The outdoor room section is the condensing sections for the heat 
pump units (compressors and outdoor coils) plus the outdoor airflow 
chamber. Conditioned outdoor air enters the outdoor coil and is 
exhausted to the outdoor room. Outdoor airflow rates were not 
measured for these units. Air is drawn in through all sides of the 
outdoor unit and discharged through the top of the unit. A sampler 
mounted around the outdoor coils measured dry-bulb temperature and 
relative humidity as it entered the condensers.
    The instrumentation for all tests is divided into air-side and 
refrigerant-side measurements. The air-side temperature measurements 
for both the inlet and outlet of the indoor coil unit are made using 
type-T thermocouple grids. A combination of dew point and relative 
humidity sensors were used for the inlet and outlet of indoor coil 
unit. For the outdoor unit, both temperature and humidity were 
measured on the inlet side of the condenser. Because the indoor 
enthalpy method was used for all tests, condenser outlet RH was not 
measured. Both inlet and outlet temperatures were be measured with 
type-T thermocouples.
BILLING CODE 6450-01-P
[GRAPHIC] [TIFF OMITTED] TN20AP07.004

    Refrigerant-side temperatures and pressures were measured 
throughout the system. Refrigerant-side test points are shown on 
Figure 2. With the exception of the refrigerant flow rate, the 
outdoor unit power, and the air flow differential pressure, the rest 
of the measurements are temperatures (dry-bulb, wet-bulb, dew point) 
and pressures. Refrigerant mass flow was measured with a Coriolis-
type flow meter placed on the liquid line after the condensing 
section of the heat pump unit (Figure A.2) for both heat pumps 
units. Separate mass flow meters were used for each heat pump unit.
    The data acquisition system converted signals coming from all 
the sensors in the indoor and outdoor rooms into temperatures, 
pressures, flow rates, or power. A data logger was used to collect 
data from the testing apparatus. The logger is linked to a computer 
where the data was visually displayed during testing. Once a test 
was complete, the data was transferred to another computer for 
processing. Each channel was scanned by the logger at regular 
intervals and the data was stored every thirty seconds. A minimum of 
one hour of steady state data was collected as per the standard's 
specifications for cooling and 30 minutes for heating. For cooling 
tests A and B, steady state was maintained for one hour before the 
start of data collection in order to ensure that steady state 
dehumidification had been achieved. A description of the data 
acquisition test points is listed in Table 1.

[[Page 19905]]

[GRAPHIC] [TIFF OMITTED] TN20AP07.005

BILLING CODE 6450-01-C
    The test procedure consisted of setting up the CES unit as per 
manufacturer's recommendations, charging the system(s), installing 
the appropriate instrumentation,

[[Page 19906]]

and running the selected tests. The tests conducted were selected by 
following the Standard, HRCU-A-CB. The Standard did not describe how 
to test a unit with eight indoor blowers, dual circuited evaporator 
coil and two heat pump units. Since the Standard did describe how to 
test a unit with two compressors which closely models the heat 
pumps, it was decided to follow the two compressor model of the 
Standard for all tests. Because of the way the CES proprietary 
control system operated the eight indoor blowers, it was decided to 
use 400 cfm per ton air flow for each compressor (2.5 ton heat 
pump).
    When test points were selected from the guidelines, tests were 
conducted at the appropriate indoor and outdoor temperatures for 
single heat pump operation and when both heat pump units were 
operating. There were three exceptions. When in cooling mode, Test C 
was conducted for full load operation only. When in heating mode the 
62F test was conducted with only single heat pump in operation while 
the 17F test was conducted for dual condenser operation only. The 
test point room conditions were as specified by the Standard 210/240 
guidelines.
    When cooling tests were conducted the moisture measurements were 
made using chilled mirror hygrometers in combination with relative 
humidity sensors as a backup. In addition to the two sensors, 
condensate was collected during all A and B tests. The energy 
balances were based on the amount of condensate collected. During 
the last few cooling tests, the hygrometer used to measure moisture 
at the evaporator exit failed. For these tests, the sensible 
capacity was calculated using the formula btuh = 
1.1\*\cfm\*\(T<INF>air--entering</INF>-T<INF>air--exiting</INF>). 
The latent capacity was calculated from the measured condensate for 
all A and B tests. For heating tests, the chilled mirror hygrometers 
were replaced with relative humidity sensors.

Results

    A summary of the results of the tests for the full load 
operation of the Cascade Energy Saver (two heat pumps and eight 
indoor blowers at a total of 2000 cfm) (hereinafter referred to as 
``Full Capacity'') are included in Table 3 below. A detailed summary 
of each test is included in the pages that follow.

                   Table 3.--Summary of the Results of the Tests for the Cascade Energy Saver
                          [The test results are for the unit running at full capacity]
----------------------------------------------------------------------------------------------------------------
                                                                                    Total power
                                                      Total capacity (btuh)            (kW)             EER
----------------------------------------------------------------------------------------------------------------
                                                     Cooling
----------------------------------------------------------------------------------------------------------------
A.............................................  65,201..........................             4.4            14.8
B.............................................  63,766..........................             3.8            16.6
C.............................................  58,393..........................             3.9            15.0
SEER..........................................  18.1............................  ..............  ..............
----------------------------------------------------------------------------------------------------------------
                                                Total capacity..................     Total power             COP
                                                (btuh)..........................            (kW)
----------------------------------------------------------------------------------------------------------------
                                                     Heating
----------------------------------------------------------------------------------------------------------------
62F...........................................  37,979 (1 comp).................             3.1             3.6
47F...........................................  67,827..........................             5.7             3.5
35F...........................................  56,561..........................             5.2             3.2
17F...........................................  37,645..........................             4.5             2.5
HSPF..........................................  9.5.............................  ..............  ..............
----------------------------------------------------------------------------------------------------------------


                                                 Results Cooling
----------------------------------------------------------------------------------------------------------------
 
----------------------------------------------------------------------------------------------------------------
                                     Test A. Single Heat Pump, Four Blowers
----------------------------------------------------------------------------------------------------------------
                                         System Average Performance Data
----------------------------------------------------------------------------------------------------------------
System EER.........................  14.2.......................................  Btu/hr-W.
Sensible heat factor...............  0.8........................................  %.
System Capacity....................  29576.6....................................  Btu/hr.
Total System Power.................  2.1........................................  KW.
NRG Bal (refside, cond)............  5.2........................................  % Diff.
NRG Bal (refside, dps).............  7.5........................................  % Diff.
----------------------------------------------------------------------------------------------------------------
                                             Indoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb..............  80.0 +/-...................................  0.08 Deg F.
Air Entering Wet Bulb..............  66.7 +/-...................................  0.15 Deg F.
Air Entering Enthalpy..............  31.2 +/-...................................  0.12 Btu/lb.
Air Exiting Dry Bulb...............  58.5 +/-...................................  0.18 Deg F.
Air Exiting Enthalpy...............  25.1 +/-...................................  0.32 Btu/lb.
Air Flow Rate......................  1033.5 +/-.................................  7.89 CFM.
Measured Fan Power.................  0.2 +/-....................................  0 KW.
Refrig Entering pressure...........  212.5 +/-..................................  0.65 Psia.
Refrig Entering temp...............  99.1 +/-...................................  0.22 Deg F.
Refrig Exiting pressure............  82.9 +/-...................................  0.22 Psia.
Refrig Exiting Temp................  72.5 +/-...................................  1.08 Deg F.
Air Side SensCap...................  24464.7....................................  Btu/hr.
AS CondLatentCap...................  5111.9.....................................  Btu/hr.
AS EstLatentCap....................  4396.2.....................................  Btu/hr.
AS Cap Cond........................  29576.6....................................  Btu/hr.
AS Cap Est.........................  28860.8....................................  Btu/hr.

[[Page 19907]]

 
Refrigerant Side Capacity..........  31206.7 +/-................................  131.26 Btu/hr.
----------------------------------------------------------------------------------------------------------------
                                             Outdoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb..............  94.5 +/-...................................  0.22 Deg F.
Suction Pressure...................  83.4 +/-...................................  0.23 Psia.
Suction Temperature................  63.1 +/-...................................  0.74 Deg F.
Liquid Line pressure...............  217.6......................................  0.66 Psia.
Liquid Line Temperature............  105.5 +/-..................................  0.25 Deg F.
----------------------------------------------------------------------------------------------------------------
                                           Mass Flow Meter Conditions
----------------------------------------------------------------------------------------------------------------
Refrigerant flow rate..............  7.0 +/-....................................  0.02 Lb/min.
Entering pressure..................  217.2 +/-..................................  0.66 Psia.
Entering temperature...............  104.6 +/-..................................  0.25 Deg F.
Exiting pressure...................  214.2 +/-..................................  0.65 Psia.
Exiting temperature................  103.7 +/-..................................  0.24 Psia.
----------------------------------------------------------------------------------------------------------------
                                      Test A. Two Heat Pump, Eight Blowers
----------------------------------------------------------------------------------------------------------------
Test Description...................  ARI 210-240 Test A.........................
Start of Test......................  5/22/04....................................  5:21:59 PM.
End of Test........................  5/22/04....................................  6:21:59 PM.
Number of Data Scans...............  3289.......................................
----------------------------------------------------------------------------------------------------------------
                                         System Average Performance Data
----------------------------------------------------------------------------------------------------------------
System EER.........................  14.8.......................................  Btu/hr-W.
Sensible heat factor...............  0.8........................................  %.
System Capacity....................  65201.2....................................  Btu/hr.
Total System Power.................  4.4........................................  KW.
NRG Bal (refside, cond)............  -2.6.......................................  % Diff.
----------------------------------------------------------------------------------------------------------------
                                             Indoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb..............  79.8 +/-...................................  0.42 Deg F.
Air Entering Wet Bulb..............  67.0 +/-...................................  0.31 Deg F.
Air Exiting Dry Bulb...............  58.1 +/-...................................  0.27 Deg F.
Air Flow Rate......................  2070.9 +/-.................................  0.35 CFM.
Measured Fan Power.................  0.4 +/-....................................  0.26 KW.
Air Side SensCap...................  49637.4....................................  Btu/hr.
AS CondLatentCap...................  13849.3....................................  Btu/hr.
AS Cap Cond........................  63486.8....................................  Btu/hr.
Refrigerant Side Capacity..........  65201.2....................................  Btu/hr.
----------------------------------------------------------------------------------------------------------------
                                             Outdoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb 1............  95.0 +/-...................................  0.3 Deg F.
Air Entering Dry Bulb 2............  94.5 +/-...................................  0.3 Deg F.
Measured Power.....................  4.0 +/-....................................  0.0 KW.
----------------------------------------------------------------------------------------------------------------
                                           Mass Flow Meter Conditions
----------------------------------------------------------------------------------------------------------------
Refrigerant flow rate 1............  7.9 +/-....................................  0.0 Lb/min.
Refrigerant flow rate 2............  7.2 +/-....................................  0.0 Lb/min.
Total Mass Flow Rate...............  15.0.......................................  0.0 Lb/min.
----------------------------------------------------------------------------------------------------------------
                                     Test B. Single Heat Pump, Four Blowers
----------------------------------------------------------------------------------------------------------------
                                         System Average Performance Data
----------------------------------------------------------------------------------------------------------------
System EER.........................  17.8.......................................  Btu/hr-W.
Sensible heat factor...............  0.8........................................  %.
System Capacity....................  31891.5....................................  Btu/hr.
Total System Power.................  1.8........................................  KW.
NRG Bal (refside, cond)............  0.5........................................  % Diff.
NRG Bal (refside, dps).............  -1.2.......................................  % Diff.
----------------------------------------------------------------------------------------------------------------
                                             Indoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb..............  80.0 +/-...................................  0.06 Deg F.
Air Entering Wet Bulb..............  67.1 +/-...................................  0.05 Deg F.
Air Entering Enthalpy..............  31.5 +/-...................................  0.04 Btu/lb.
Air Exiting Dry Bulb...............  58.6 +/-...................................  0.1 Deg F.
Air Exiting Enthalpy...............  24.9 +/-...................................  0.41 Btu/lb.

[[Page 19908]]

 
Air Flow Rate......................  1084.5 +/-.................................  3.99 CFM.
Measured Fan Power.................  0.2 +/-....................................  0 KW.
Refrig Entering pressure...........  175.6 +/-..................................  0.31 Psia.
Refrig Entering temp...............  87.7 +/-...................................  0.12 Deg F.
Refrig Exiting pressure............  79.3 +/-...................................  0.16 Psia.
Refrig Exiting Temp................  81.4 +/-...................................  0.47 Deg F.
Air Side SensCap...................  26042.4....................................  Btu/hr.
AS CondLatentCap...................  5849.1.....................................  Btu/hr.
AS EstLatentCap....................  6384.3.....................................  Btu/hr.
AS Cap Cond........................  31891.5....................................  Btu/hr.
AS Cap Est.........................  32426.7....................................  Btu/hr.
Refrigerant Side Capacity..........  32048.9 +/-................................  93.46 Btu/hr.
----------------------------------------------------------------------------------------------------------------
                                             Outdoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb..............  81.7 +/-...................................  0.12 Deg F.
Suction Pressure...................  79.5 +/-...................................  0.15 Psia.
Suction Temperature................  68.6 +/-...................................  0.26 Deg F.
Liquid Line pressure...............  180.1 +/-..................................  0.32 Psia.
Liquid Line Temperature............  91.4 +/-...................................  0.14 Deg F.
----------------------------------------------------------------------------------------------------------------
                                           Mass Flow Meter Conditions
----------------------------------------------------------------------------------------------------------------
Refrigerant flow rate..............  6.7 +/-....................................  0.02 Lb/min.
Entering pressure..................  180.2 +/-..................................  0.32 Psia.
Entering temperature...............  90.5 +/-...................................  0.14 Deg F.
Exiting pressure...................  177.3 +/-..................................  0.31 Psia.
Exiting temperature................  89.7 +/-...................................  0.14 Psia.
----------------------------------------------------------------------------------------------------------------
                                      Test B. Two Heat Pumps, Eight Blowers
----------------------------------------------------------------------------------------------------------------
Test Description...................  ARI 210-240 Test B.........................  ..............................
Start of Test......................  5/24/04....................................  5:00:00 PM.
End of Test........................  5/24/04....................................  6:00:00 PM.
Number of Data Scans...............  3332.......................................
----------------------------------------------------------------------------------------------------------------
                                         System Average Performance Data
----------------------------------------------------------------------------------------------------------------
System EER.........................  16.6.......................................  Btu/hr-W.
Sensible heat factor...............  0.7........................................  %.
System Capacity....................  63765.7....................................  Btu/hr.
Total System Power.................  3.8........................................  KW.
NRG Bal (refside, cond)............  4.6........................................  % Diff.
----------------------------------------------------------------------------------------------------------------
                                             Indoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb..............  80.4 +/-...................................  0.14 Deg F.
Air Entering Wet Bulb..............  67.4 +/-...................................  0.17 Deg F.
Air Exiting Dry Bulb...............  58.4 +/-...................................  0.15 Deg F.
Air Flow Rate......................  2071.6 +/-.................................  0.28 CFM.
Measured Fan Power.................  0.4 +/-....................................  0.21 KW.
Air Side SensCap...................  49974.3....................................  Btu/hr.
AS CondLatentCap...................  16706.2....................................  Btu/hr.
AS Cap Cond........................  66680.5....................................  Btu/hr.
Refrigerant Side Capacity..........  63765.7....................................  Btu/hr.
----------------------------------------------------------------------------------------------------------------
                                             Outdoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb 1............  82.4 +/-...................................  0.2 Deg F.
Air Entering Dry Bulb 2............  81.9 +/-...................................  0.2 Deg F.
Measured Power.....................  3.4 +/-....................................  0.0 KW.
----------------------------------------------------------------------------------------------------------------
                                           Mass Flow Meter Conditions
----------------------------------------------------------------------------------------------------------------
Refrigerant flow rate 1............  7.1 +/-....................................  0.0 Lb/min.
Refrigerant flow rate 2............  7.0 +/-....................................  0.0 Lb/min.
Total Mass Flow Rate...............  14.1.......................................  0.0 Lb/min.
----------------------------------------------------------------------------------------------------------------
                                      Test C. Two Heat Pumps, Eight Blowers
----------------------------------------------------------------------------------------------------------------
Test Description...................  ARI 210-240 Test C.........................
Start of Test......................  2/05/2004..................................  1:08:04 PM.
End of Test........................  2/05/2004..................................  2:09:25 PM.
Number of Data Scans...............  3438.......................................
----------------------------------------------------------------------------------------------------------------

[[Page 19909]]

 
                                         System Average Performance Data
----------------------------------------------------------------------------------------------------------------
System EER.........................  15.0.......................................  Btu/hr-W.
Sensible heat factor...............  1.0........................................  %.
System Capacity....................  58392.9....................................  Btu/hr.
Total System Power.................  3.9........................................  KW.
NRG Bal (refside, cond)............  2.0........................................  % Diff.
----------------------------------------------------------------------------------------------------------------
                                             Indoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb..............  80.4 +/-...................................  0.13 Deg F.
Air Entering Wet Bulb..............  41.2 +/-...................................  0.00 Deg F.
Air Exiting Dry Bulb...............  53.5 +/-...................................  0.15 Deg F.
Air Flow Rate......................  2010.4 +/-.................................  0.24 CFM.
Measured Fan Power.................  0.4 +/-....................................  0.00 KW.
Air Side SensCap...................  59532.7....................................  Btu/hr.
AS CondLatentCap...................  0..........................................  Btu/hr.
AS Cap Cond........................  59532.7....................................  Btu/hr.
Refrigerant Side Capacity..........  58392.9....................................  Btu/hr.
----------------------------------------------------------------------------------------------------------------
                                             Outdoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb 1............  82.6 +/-...................................  0.1 Deg F.
Air Entering Dry Bulb 2............  83.5 +/-...................................  0.3 Deg F.
Measured Power.....................  3.5 +/-....................................  0.0 KW.
----------------------------------------------------------------------------------------------------------------
                                           Mass Flow Meter Conditions
----------------------------------------------------------------------------------------------------------------
Refrigerant flow rate 1............  12.9 +/-...................................  0.0 Lb/min.
Total Mass Flow Rate...............  12.9.......................................  0.0 Lb/min.
----------------------------------------------------------------------------------------------------------------


                                                SEER Calculations
----------------------------------------------------------------------------------------------------------------
                                                                One comp     Two comp     One comp     Two comp
----------------------------------------------------------------------------------------------------------------
OAT                                                                    Q1           Q2           E1           E2
----------------------------------------------------------------------------------------------------------------
95..........................................................     29576.58        65201         2.08          4.4
82..........................................................     31891.51        66680         1.79          3.8


--------------------------------------------------------------------------------------------------------------------------------------------------------
                          Step                                 j         Nj/N       BL(Tj)      X(k=1)      X(k=2)        PLF       Q(T)?N      E(T)/N
--------------------------------------------------------------------------------------------------------------------------------------------------------
1.......................................................          67       0.214    3951.576       0.124       0.000       0.781       845.6         0.1
2.......................................................          72       0.231   13830.515       0.434       0.000       0.858      3194.8         0.2
3.......................................................          77       0.216   23709.455       0.743       0.000       0.936      5121.2         0.3
4.......................................................          82       0.161   33588.394       1.053       0.000       1.013      5407.7         0.3
5.......................................................          87       0.104   43467.333       0.652       0.348       0.913      4520.6         0.1
6.......................................................          92       0.052   53346.273       0.356       0.644  ..........      2774.0         0.2
7.......................................................          97       0.018   63225.212       0.059       0.941  ..........      1173.6         0.1
8.......................................................         102       0.004   73104.152      -0.237       1.237  ..........       260.8         0.0
Sum Q(T)................................................     23298.5  ..........  ..........  ..........  ..........  ..........     23298.5         1.3
Sum E (T)...............................................         1.3  ..........  ..........  ..........  ..........  ..........  ..........  ..........
SEER....................................................        18.1  ..........  ..........  ..........  ..........  ..........  ..........  ..........
--------------------------------------------------------------------------------------------------------------------------------------------------------


                                                 Results Heating
----------------------------------------------------------------------------------------------------------------
 
----------------------------------------------------------------------------------------------------------------
                                Test 62F Outdoor, Single Heat Pump, Four Blowers
----------------------------------------------------------------------------------------------------------------
Test Description...................  ARI 210-240 Heating 62 F OAT...............
Start of Test......................  8/08/2004..................................  2:30:00 PM.
End of Test........................  2/05/2004..................................  3:06:33 PM.
Number of Data Scans...............  2182.......................................
----------------------------------------------------------------------------------------------------------------
                                         System Average Performance Data
----------------------------------------------------------------------------------------------------------------
System COP.........................  3.6........................................
System Capacity....................  37048.4....................................  Btu/hr.
Total System Power.................  3.1........................................  KW.
NRG Bal (refside)..................  -2.5.......................................  %.
----------------------------------------------------------------------------------------------------------------

[[Page 19910]]

 
                                             Indoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb..............  69.61 +/-..................................  0.26 Deg F.
Air Entering RH....................  46.27 +/-..................................  0.07%.
Air exiting Wet Bulb...............  57.16 +/-..................................  0.22 Deg F.
Air Exiting Dry Bulb...............  111.2 +/-..................................  0.37 Deg F.
Air Flow Rate......................  945.4......................................  CFM.
Measured Fan Power.................  0.2 +/-....................................  0.00 KW.
Air Side SensCap...................  37979.1....................................  Btu/hr.
Refrigerant Side Capacity..........  37048.4....................................  Btu/hr.
----------------------------------------------------------------------------------------------------------------
                                             Outdoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb 1............  61.8 +/-...................................  0.3 Deg F.
Air Entering Dry Bulb 2............  62.5 +/-...................................  0.3 Deg F.
Measured Power.....................  2.9+/-.....................................  0.2 KW.
----------------------------------------------------------------------------------------------------------------
                                           Mass Flow Meter Conditions
----------------------------------------------------------------------------------------------------------------
Refrigerant flow rate 1............  7.5 +/-....................................  0.1 Lb/min
Total Mass Flow Rate...............  7.5........................................  0.0 Lb/min.
----------------------------------------------------------------------------------------------------------------
                                   47F Outdoor, Single Heat Pump, Four Blowers
----------------------------------------------------------------------------------------------------------------
Test Description...................  ARI 210-240 Heating 47 F OAT...............
Start of Test......................  7/18/2004..................................  7:24:11 PM.
End of Test........................  7/18/2004..................................  7:54:49 PM.
Number of Data Scans...............  1601.......................................
----------------------------------------------------------------------------------------------------------------
                                         System Average Performance Data
----------------------------------------------------------------------------------------------------------------
System COP.........................  3.3........................................
System Capacity....................  3058303....................................  Btu/hr.
Total System Power.................  2.8........................................  KW.
NRG Bal (refside)..................  -4.9.......................................  %.
----------------------------------------------------------------------------------------------------------------
                                             Indoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb..............  69.2 +/-...................................  0.43 Deg F.
Air Entering RH....................  57.2 +/-...................................  3.11%.
Air exiting Wet Bulb...............  59.6 +/-...................................  1.14 Deg F.
Air Exiting Dry Bulb...............  102.6 +/-..................................  0.43 Deg F.
Air Flow Rate......................  969.3......................................  CFM.
Measured Fan Power.................  0.2 +/-....................................  0.00 KW.
Air Side SensCap...................  32093.2....................................  Btu/hr.
Refrigerant Side Capacity..........  30583.3....................................  Btu/hr.
----------------------------------------------------------------------------------------------------------------
                                             Outdoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb 1............  46.4 +/-...................................  0.4 Deg F.
Air Entering Dry Bulb 2............  47.6 +/-...................................  0.6 Deg F.
Measured Power.....................  2.6+/-.....................................  0.0 KW.
----------------------------------------------------------------------------------------------------------------
                                           Mass Flow Meter Conditions
----------------------------------------------------------------------------------------------------------------
Refrigerant flow rate 1............  6.1 +/-....................................  0.1 Lb/min.
Total Mass Flow Rate...............  6.1........................................  0.0 Lb/min.
----------------------------------------------------------------------------------------------------------------
                                   47F Outdoor, Two Heat Pumps, Eight Blowers
----------------------------------------------------------------------------------------------------------------
Test Description...................  ARI 210-240 Heating 47 F OAT...............
Start of Test......................  7/8/2004...................................  11:12:00 PM.
End of Test........................  7/8/2004...................................  12:00:00 PM.
Number of Data Scans...............  1042.......................................
----------------------------------------------------------------------------------------------------------------
                                         System Average Performance Data
----------------------------------------------------------------------------------------------------------------
System COP.........................  3.5........................................
System Capacity....................  70140.0....................................  Btu/hr.
Total System Power.................  5.7........................................  KW.
NRG Bal (refside)..................  3.3........................................  %.
----------------------------------------------------------------------------------------------------------------

[[Page 19911]]

 
                                             Indoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb..............  70.2 +/-...................................  0.25 Deg F.
Air Entering RH....................  51.8 +/-...................................  0.33%.
Air exiting Wet Bulb...............  59.1 +/-...................................  0.29 Deg F.
Air Exiting Dry Bulb...............  104.5 +/-..................................  0.22 Deg F.
Air Flow Rate......................  969.3......................................  CFM.
Measured Fan Power.................  0.4 +/-....................................  0.01 KW.
Air Side SensCap...................  67826.8....................................  Btu/hr.
Refrigerant Side Capacity..........  70140.0....................................  Btu/hr.
----------------------------------------------------------------------------------------------------------------
                                             Outdoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb 1............  46.8 +/-...................................  0.3 Deg F.
Air Entering Dry Bulb 2............  47.6 +/-...................................  0.3 Deg F.
Measured Power.....................  5.2+/-.....................................  0.0 KW.
----------------------------------------------------------------------------------------------------------------
                                           Mass Flow Meter Conditions
----------------------------------------------------------------------------------------------------------------
Refrigerant flow rate 1............  5.9 +/-....................................  0.0 Lb/min.
Refrigerant flow rate 1............  5.7 +/-....................................  0.0 Lb/min.
Total Mass Flow Rate...............  11.7.......................................
----------------------------------------------------------------------------------------------------------------
                                   35F Outdoor, Single Heat Pump, Four Blowers
----------------------------------------------------------------------------------------------------------------
Test Description...................  ARI 210-240 Heating 35 F OAT...............
Start of Test......................  7/13/2004..................................  12:30:30 PM.
End of Test........................  7/13/2004..................................  12:00:00 AM.
Number of Data Scans...............  1562.......................................
----------------------------------------------------------------------------------------------------------------
                                         System Average Performance Data
----------------------------------------------------------------------------------------------------------------
System COP.........................  3.1........................................
System Capacity....................  25654.6....................................  Btu/hr.
Total System Power.................  2.6........................................  KW.
NRG Bal (refside)..................  -5.7.......................................  %.
----------------------------------------------------------------------------------------------------------------
                                             Indoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb..............  70.5 +/-...................................  0.41 Deg F.
Air Entering RH....................  60.8 +/-...................................  0.44%.
Air exiting Wet Bulb...............  61.6 +/-...................................  0.46 Deg F.
Air Exiting Dry Bulb...............  98.0 +/-...................................  3.79 Deg F.
Air Flow Rate......................  1013.0.....................................  CFM.
Measured Fan Power.................  0.2 +/-....................................  0.00 KW.
Air Side SensCap...................  27123.9....................................  Btu/hr.
Refrigerant Side Capacity..........  25654.6....................................  Btu/hr.
----------------------------------------------------------------------------------------------------------------
                                             Outdoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb 1............  34.9 +/-...................................  0.2 Deg F.
Air Entering Dry Bulb 2............  35.4 +/-...................................  0.3 Deg F.
Measured Power.....................   2.4+/-....................................  0.1 KW.
----------------------------------------------------------------------------------------------------------------
                                           Mass Flow Meter Conditions
----------------------------------------------------------------------------------------------------------------
Refrigerant flow rate 1............  5.1 +/-....................................  0.8 Lb/min.
Total Mass Flow Rate...............  5.1........................................
----------------------------------------------------------------------------------------------------------------
                                    35F Outdoor, Two Heat Pump, Eight Blowers
----------------------------------------------------------------------------------------------------------------
Test Description...................  ARI 210-240 Heating 35 F OAT...............
Start of Test......................  7/13/2004..................................  9:56:30 AM.
End of Test........................  7/13/2004..................................  12:00:00 AM.
Number of Data Scans...............  1591.......................................
----------------------------------------------------------------------------------------------------------------
                                         System Average Performance Data
----------------------------------------------------------------------------------------------------------------
System COP.........................  3.5........................................
System Capacity....................  58219.2....................................  Btu/hr.
Total System Power.................  4.8........................................  KW.
NRG Bal (refside)..................  2.8........................................  %.
----------------------------------------------------------------------------------------------------------------

[[Page 19912]]

 
                                             Indoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb..............  70.1 +/-...................................  0.23 Deg F.
Air Entering RH....................  61.9 +/-...................................  0.29%.
Air exiting Wet Bulb...............  61.5 +/-...................................  0.27 Deg F.
Air Exiting Dry Bulb...............  99.2 +/-...................................  0.19 Deg F.
Air Flow Rate......................  1978.7.....................................  CFM.
Measured Fan Power.................  0.4 +/-....................................  0.00 KW.
Air Side SensCap...................  56561.2....................................  Btu/hr.
Refrigerant Side Capacity..........  58219.2....................................  Btu/hr.
----------------------------------------------------------------------------------------------------------------
                                             Outdoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb 1............  34.5 +/-...................................  0.5 Deg F.
Air Entering Dry Bulb 2............  34.7 +/-...................................  0.6 Deg F.
Measured Power.....................  4.4+/-.....................................  0.2 KW.
----------------------------------------------------------------------------------------------------------------
                                           Mass Flow Meter Conditions
----------------------------------------------------------------------------------------------------------------
Refrigerant flow rate 1............  5.1 +/-....................................  0.1 Lb/min.
Refrigerant flow rate 1............  4.7 +/-....................................  0.1 Lb/min.
Total Mass Flow Rate...............  9.8........................................
----------------------------------------------------------------------------------------------------------------
                                   17F Outdoor, Two Heat Pumps, Eight Blowers
----------------------------------------------------------------------------------------------------------------
Test Description...................  ARI 210-240 Heating 17 F OAT...............
Start of Test......................  8/5/2004...................................  3:54:45 PM.
End of Test........................  8/5/2004...................................  4:19:38 PM.
Number of Data Scans...............  1485.......................................
----------------------------------------------------------------------------------------------------------------
                                         System Average Performance Data
----------------------------------------------------------------------------------------------------------------
System COP.........................  2.4........................................
System Capacity....................  37645.5....................................  Btu/hr.
Total System Power.................  4.5........................................  KW.
NRG Bal (refside)..................  -88.3......................................  %.
----------------------------------------------------------------------------------------------------------------
                                             Indoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb..............  70.1 +/-...................................  0.67 Deg F.
Air Entering RH....................  53.0 +/-...................................  0.53%.
Air exiting Wet Bulb...............  59.2 +/-...................................  0.65 Deg F.
Air Exiting Dry Bulb...............  90.3 +/-...................................  0.68 Deg F.
Air Flow Rate......................  1911.5.....................................  CFM.
Measured Fan Power.................  0.4 +/-....................................  0.00 KW.
Air Side SensCap...................  37645.5....................................  Btu/hr.
Refrigerant Side Capacity..........  19993.6....................................  Btu/hr.
----------------------------------------------------------------------------------------------------------------
                                             Outdoor Coil Conditions
----------------------------------------------------------------------------------------------------------------
Air Entering Dry Bulb 1............  16.6 +/-...................................  0.3 Deg F.
Air Entering Dry Bulb 2............  16.0 +/-...................................  0.3 Deg F.
Measured Power.....................  4.1+/-.....................................  0.0 KW.
----------------------------------------------------------------------------------------------------------------
                                           Mass Flow Meter Conditions
----------------------------------------------------------------------------------------------------------------
Refrigerant flow rate 1............  3.8 +/-....................................  0.0 Lb/min.
Refrigerant flow rate 1............  3.3 +/-....................................  0.1 Lb/min.
Total Mass Flow Rate...............  7.1........................................
----------------------------------------------------------------------------------------------------------------

BILLING CODE 6450-01-P

[[Page 19913]]

[GRAPHIC] [TIFF OMITTED] TN20AP07.006

[FR Doc. 07-1887 Filed 4-19-07; 8:45 am]
BILLING CODE 6450-01-C


</pre><script data-cfasync="false" src="/cdn-cgi/scripts/5c5dd728/cloudflare-static/email-decode.min.js"></script></body>
</html>