alea-institute/kl3m-data-sample-004-shuffled huggingface dataset:
§ 111.30-27 Direct current ship's service switchboards. ( a ) Each direct current ship's service switchboard must have the equipment required by paragraphs (b) through (f) of this section.
( b ) For each connected generator, each switchboard must have the following: ( 1 ) A circuit breaker that meets § 111.12-11 and § 111.50-5.
( 2 ) A disconnect switch or link for each generator conductor, except a switchboard having a draw-out or plug-in type generator circuit breaker that disconnects— ( i ) Each conductor; or
( ii ) If there is a switch in the generator neutral, each ungrounded conductor.
( 3 ) A field rheostat.
( 4 ) An indicator light connected between the generator and circuit breaker.
( c ) For each two-wire generator, each switchboard must have: ( 1 ) An ammeter; and
( 2 ) A voltmeter with a selector switch that connects the voltmeter to show: ( i ) Generator voltage; and
( ii ) Bus voltage.
( d ) For each three-wire generator, each switchboard must have the following: ( 1 ) An ammeter for: ( i ) The positive lead; and
( ii ) The negative lead.
( 2 ) A center zero type ammeter for the neutral ground connection.
( 3 ) A voltmeter with a selector switch that connects the voltmeter to show generator and bus voltage: ( i ) Positive to negative;
( ii ) Positive to neutral; and
( iii ) Neutral to negative.
( e ) Each switchboard must have ground detection that meets subpart 111.05 for the: ( 1 ) Main power system;
( 2 ) Main lighting system; and
( 3 ) Emergency lighting system.
( f ) For each shore power connection, each switchboard must have: ( 1 ) A circuit breaker or fused switch; and
( 2 ) A pilot light connected to the shore side.
( g ) One of the voltmeters under paragraph (c)(2) or (d)(3) of this section must be connected to show: ( 1 ) For each two-wire system, shore connection voltage; and
( 2 ) For each three-wire system, shore connection voltage: ( i ) Positive to negative;
( ii ) Positive to neutral; and
( iii ) Neutral to negative.
[CGD 74-125A, 47 FR 15236, Apr. 8, 1982, as amended by USCG-2020-0075, 88 FR 16361, Mar. 16, 2023]
**Exhibit 32**

 

CERTIFICATION PURSUANT TO

18 U.S.C. SECTION 1350,

AS ADOPTED PURSUANT TO

SECTION 906 OF THE SARBANES-OXLEY ACT OF 2002

 

In connection with the Quarterly Report of Artificial Life, Inc. (the "Company") on Form 10-QSB for the period ended September 30, 2007 as filed with the Securities and Exchange Commission on the date hereof (the "Report"), I, Eberhard Schoneburg, Chief Executive Officer and Principal Financial Officer of the Company, certify, pursuant to 18 U.S.C. ss. 1350, as adopted pursuant to ss. 906 of the Sarbanes-Oxley Act of 2002, that:

 

|   | (1) The Report fully complies with the requirements of section 13(a) or 15(d) of the Securities Exchange Act of 1934; and |
|--------|---------------------------------------------------------------------------------------------------------------------------|

 

(2) The information contained in the Report fairly presents, in all material respects, the financial condition and result of operations of the Company.

 

/s/ Eberhard Schoneburg

 

      Eberhard Schoneburg

        Chief Executive Officer and

      Principal Financial Officer

 

November 8, 2007

 

 

----
Exhibit 32.1

CERTIFICATION PURSUANT TO

18 U.S.C. SECTION 1350,

AS ADOPTED PURSUANT TO

SECTION 906
OF THE SARBANES-OXLEY ACT OF 2002

In connection with the Quarterly Report of First Capital, Inc. and Subsidiaries (the
Company) on Form 10-Q for the period ended March 31, 2006, as filed with the Securities and Exchange Commission (the Report), I, William W. Harrod, President and Chief Executive Officer of the Company, certify, pursuant
to 18 U.S.C. Section 1350, as adopted pursuant to Section 906 of the Sarbanes-Oxley Act of 2002, that:



| | (1) | The Report fully complies with the requirements of Section 13(a) or 15(d) of the Securities Exchange Act of 1934; and
| | --- | ---------------------------------------------------------------------------------------------------------------------



| | (2) | The information contained in the Report fairly presents, in all material respects, the financial condition and results of operations of the Company as of and for the period covered
by the Report.
| | --- | ---------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------



|
|



|      |  |              |  |  |  |     |  |                                                                                      
|----- |  | ------------ |  |  |  | --- |  | -------------------------------------------------------------------------------------
|      |  |              |  | 
|DATE: |  | May 12, 2006 |  |  |  | BY: |  | /s/    WILLIAM W. HARROD                                                             
|      |  |              |  |  |  |     |  | William W. Harrod President and Chief Executive Officer (Principal Executive Officer)
May 10, 2012

Ms. Colleen Gillespie Chief Wastewater Permitting Unit U.S. EPA, Region VIII 1595 Wynkoop Street
Denver, CO 80202

- 8917

Re: Section 401 Water Quality Certification for Proposed 2013 Vessel General Permit

Dear Ms. Gillespie :

T he Water Quality Control Division (Division) has reviewed the above draft NPDES permit. Provided the facility covered under the permit complies with the permit conditions, the Division is reasonably assured the Colorado Water Quality Control Act will not b e violated by these activities. The Division conducted public notice from December 30, 2011 through January 30, 2012 regarding its intent to certify this draft permit without additional conditions. No public comments were received.

If the permit ch anges from the public notice version, based on comments received during public notice, the Division would like to be informed of these changes as they may render this determination null and

void.

This certification does not constitute a relinquishment of the Division’s authority as delineated in the “Colorado Water Quality Control Act,” or any subsequent alterations thereto, nor does it fulfill or waive any other local, state or federal regulations.

If you have any questions, ple ase give me a call at 303

- 692

- 3 599

Sincerely,

Janet Kieler

Permits Section Manager

Cc: File : 401 Certifications

– Federal Facilities

– Vessel General Permit
# C_2011269EN.01002903.xml

| 10.9.2011 | EN | Official Journal of the European Union | C 269/29 |
| --- | --- | --- | --- |

10.9.2011

EN

Official Journal of the European Union

C 269/29

---

Reference for a preliminary ruling from the Sąd Rejonowy w Koszalinie (Republic of Poland), lodged on 28 June 2011 — Krystyna Alder and Ewald Alder v Sabina Orłowska and Czesław Orłowski

(Case C-325/11)

2011/C 269/56

Language of the case: Polish

Referring court

Referring court

Sąd Rejonowy w Koszalinie

Parties to the main proceedings

Parties to the main proceedings

Claimants: Krystyna Alder, Ewald Alder

Claimants:

Defendants: Sabina Orłowska, Czesław Orłowski

Defendants:

Question referred

Question referred

Are Article 1(1) of Regulation (EC) No 1393/2007 of the European Parliament and of the Council of 13 November 2007 on the service in the Member States of judicial and extrajudicial documents in civil or commercial matters (1) and Article 18 of the Treaty on the Functioning of the European Union to be interpreted as meaning that it is permissible to place in the case file, deeming them to have been effectively served, court documents which are addressed to a party whose place of residence or habitual abode is in another Member State, if that party has failed to appoint a representative who is authorised to accept service and is resident in the Member State in which the court proceedings are being conducted?

1

---

(1)  Regulation (EC) No 1393/2007 of the European Parliament and of the Council of 13 November 2007 on the service in the Member States of judicial and extrajudicial documents in civil or commercial matters (service of documents), and repealing Council Regulation (EC) No 1348/2000 (OJ 2007 L 324, p. 79).

1

---
[Federal Register Volume 72, Number 74 (Wednesday, April 18, 2007)]
[Notices]
[Page 19555]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: 07-1945]


=======================================================================
-----------------------------------------------------------------------

OVERSEAS PRIVATE INVESTMENT CORPORATION


April 19, 2007 Public Hearing

    OPIC's Sunshine Act notice of its Public Hearing in Conjunction 
with each Board meeting was published in the Federal Register (Volume 
72, Number 59, Page 14627) on March 29, 2007. No requests were received 
to provide testimony or submit written statements for the record; 
therefore, OPIC's public hearing scheduled for 2 PM, April 19, 2007 in 
conjunction with OPIC's April 26, 2007 Board of Directors meeting has 
been cancelled.
    Contact Person For Information: Information on the hearing 
cancellation may be obtained from Connie M. Downs at (202) 336-8438, 
via facsimile at (202) 218-0136, or via e-mail at <a href="/cdn-cgi/l/email-protection#85e6e1eaf2ebc5eaf5ece6abe2eaf3"><span class="__cf_email__" data-cfemail="a4c7c0cbd3cae4cbd4cdc78ac3cbd2">[email protected]</span></a>.

    Dated: April 16, 2007.
Connie M. Downs,
OPIC Corporate Secretary.
[FR Doc. 07-1945 Filed 4-16-07; 1:53 pm]
BILLING CODE 3210-01-M


</pre><script data-cfasync="false" src="/cdn-cgi/scripts/5c5dd728/cloudflare-static/email-decode.min.js"></script></body>
</html>
# C_2008109EN.01002501.xml

| 30.4.2008 | EN | Official Journal of the European Union | C 109/25 |
| --- | --- | --- | --- |

30.4.2008

EN

Official Journal of the European Union

C 109/25

---

Notice for the attention of the persons, groups and entities on the list provided for in Article 2(3) of Council Regulation (EC) No 2580/2001 on specific restrictive measures directed against certain persons and entities with a view to combating terrorism

(2008/C 109/09)

The following information is brought to the attention of the Hofstadgroep listed in Council Decision 2007/868/EC.

Hofstadgroep

The Council of the European Union has determined that the reasons for including the above group on the above-mentioned lists of persons, groups and entities subject to the restrictive measures provided for under Council Regulation (EC) 2580/2001 of 27 December 2001, on specific restrictive measures directed against certain persons and entities with a view to combating terrorism, are still valid. Consequently, the Council intends to maintain this group on the list.

The attention of the group concerned is drawn to the fact that since the adoption of Decision 2007/868/EC, the Council has been provided with new information relevant to this listing. Having considered this new information, the Council intends to maintain the group concerned on the above mentioned list. Therefore, the Council has amended the statement of reasons accordingly.

The group concerned may submit a request to obtain the Council's revised statement of reasons for including and maintaining it on the above-mentioned lists to the following address:

| Council of the European Union |
| --- |
| (Attn: CP 931 designations) |
| Rue de la Loi 175 |
| B-1048 Brussels |

Council of the European Union

(Attn: CP 931 designations)

Rue de la Loi 175

B-1048 Brussels

The group concerned may submit at any time a request to the Council, together with any supporting documentation, that the decision to include and maintain it on the list should be reconsidered, to the address provided above. Such request will be considered when it is received. In this respect, the attention of the group is drawn to the regular review by the Council of the list according to Article 1(6) of Common Position 2001/931/CFSP. In order for the request to be considered at the next review, it should be submitted within one month from the date of publication of this notice.

within one month from the date of publication of this notice.

Finally, the attention of the group concerned is drawn to the possibility of making an application to the competent authorities of the relevant Member State(s) as listed in the Annex to the Regulation in order to obtain an authorisation to use frozen funds for essential needs or specific payments in accordance with Article 5(2) of that Regulation. An updated list of competent authorities is available on the web at the following address:

http://ec.europa.eu/comm/external_relations/cfsp/sanctions/measures.htm

---
###### Editorial Note on Part 160

#### Editorial Note:

Nomenclature changes to part 160 appear by USCG-2012-0832, 77 FR 59785, 59786, Oct. 1, 2012.

#### § 160.170-1 Scope.

This subpart prescribes standards, tests, and procedures for seeking Coast Guard approval of an automatic release mechanism complying with SOLAS and the IMO LSA Code, for use with davit-launched liferafts approved under subparts 160.051 or 160.151 of this part, and single-fall rescue boats approved under subpart 160.156 of this part.
§ 140.725 Additional navigation equipment. Towing vessels must be equipped with the following equipment, as applicable to the area of operation: ( a ) Fathometer (except Western Rivers).
( b ) Search light, controllable from the vessel's operating station and capable of illuminating objects at a distance of at least two times the length of the tow.
( c ) Electronic position-fixing device, satisfactory for the area in which the vessel operates, if the towing vessel engages in towing seaward of the navigable waters of the U.S. or more than 3 nautical miles from shore on the Great Lakes.
( d ) Illuminated magnetic compass or an illuminated swing-meter (Western Rivers vessels only). The compass or swing-meter must be readable from each operating station.
Note to § 140.725. Certain towing vessels subject to § 140.725 are also subject to the requirements of 33 CFR 164.72 and Automatic Identification System requirements of 33 CFR 164.46.
§ 128.240 Hydraulic or pneumatic power and control—materials and pressure design. ( a ) Each standard piping component (such as pipe runs, fittings, flanges, and standard valves) for hydraulic or pneumatic power and control systems must meet the requirements for materials and pressure design of § 128.110, 128.210, or 128.220 of this part, as appropriate.
( b ) Any non-standard hydraulic or pneumatic component (such as control valves, check valves, relief valves, and regulators) may be accepted by the cognizant OCMI or the Commanding Officer, Marine Safety Center, if the component is certified by the manufacturer as suitable for marine service and if— ( 1 ) The component meets each of the requirements for materials and pressure design of subparts 56.60 and 58.30 of this chapter and if its service is limited to the manufacturer's rated pressure; or
( 2 ) The service of the component is limited to 1 ⁄ 2 the manufacturer's recommended maximum allowable working pressure (MAWP) or 1 ⁄ 10 the component's burst pressure. Burst-pressure testing is described in ANSI B 31.1, Paragraph 104.7.A, and must be conducted to comply with Paragraph A-22, Section I, ASME Boiler and Pressure Vessel Code. Written certification of results of burst-pressure testing must be submitted with the plans required by § 127.110(d) of this subchapter.
§ 130.410 General. ( a ) Arrangements must be such that under any operating condition, including maneuvering, the safety of the vessel is equivalent to that of the same vessel with the machinery spaces fully tended and under direct manual supervision.
( b ) Acceptance by the Coast Guard of automated systems to replace specific crew members or to reduce overall requirements for crew members depends upon the— ( 1 ) Capabilities of the automated system;
( 2 ) Combination of crew members, equipment, and systems necessary to ensure the safety of the vessel, personnel, and environment in each operating condition, including maneuvering; and
( 3 ) Ability of the crew members to perform each operational evolution, including to cope with emergencies such as fire and failure of control or monitoring systems.
§ 16.201 Application. ( a ) Chemical testing of personnel must be conducted as required by this subpart and in accordance with the procedures detailed in 49 CFR part 40.
( b ) If an individual fails a chemical test for dangerous drugs under this part, the individual will be presumed to be a user of dangerous drugs.
( c ) If an individual holding a credential fails a chemical test for dangerous drugs, the individual's employer, prospective employer, or sponsoring organization must report the test results in writing to the nearest Coast Guard Officer in Charge, Marine Inspection (OCMI). The individual must be denied employment as a crewmember or must be removed from duties which directly affect the safe operation of the vessel as soon as practicable and is subject to suspension and revocation proceedings against his or her credential under 46 CFR part 5.
( d ) If an individual who does not hold a credential fails a chemical test for dangerous drugs, the individual shall be denied employment as a crewmember or removed from duties which directly affect the safe operation of the vessel as soon as possible.
( e ) An individual who has failed a required chemical test for dangerous drugs may not be re-employed aboard a vessel until the requirements of paragraph (f) of this section and 46 CFR Part 5, if applicable, have been satisfied.
( f ) Before an individual who has failed a required chemical test for dangerous drugs may return to work aboard a vessel, the MRO must determine that the individual is drug-free and the risk of subsequent use of dangerous drugs by that person is sufficiently low to justify his or her return to work. In addition, the individual must agree to be subject to increased unannounced testing— ( 1 ) For a minimum of six (6) tests in the first year after the individual returns to work as required in 49 CFR part 40; and
( 2 ) For any additional period as determined by the MRO up to a total of 60 months.
[CGD 86-607, 53 FR 47049, Nov. 11, 1988, as amended by CGD 90-014, 56 FR 31034, July 8, 1991; USCG-2000-7759, 66 FR 42968, Aug. 16, 2001; USCG-2006-24371, 74 FR 11264, Mar. 16, 2009]
This material may be protected by Copyright Law (Title 17 US Code)
This material may be protected by Copyright Law (Title 17 US Code)
This material may be protected by Copyright Law (Title 17 US Code)
This material may be protected by Copyright Law (Title 17 US Code)
This material may be protected by Copyright Law (Title 17 US Code)
This material may be protected by Copyright Law (Title 17 US Code)
This material may be protected by Copyright Law (Title 17 US Code)
#### § 108.139 Boundary bulkheads and decks of a space containing emergency power.

Each boundary bulkhead and deck of a space containing an emergency electric power source or components of an emergency electric power source must be an A class bulkhead and A class deck respectively. When separate but adjoining spaces are provided for such equipment, boundary bulkhead type construction is not required for the separating partitions common to each space.
**EXHIBIT 32.2**

**CERTIFICATION OFCHIEF FINANCIAL OFFICER**

**Pursuant toSection 906 of the Sarbanes-Oxley Act of 2002 (18 U.S.C. 1350)**

In connection with the Annual Report of First Federal Bancshares ofArkansas, Inc. (the “Registrant”) on Form 10-K for the year ended December31, 2006 as filed with the Securities and Exchange Commission (the “Report”),the undersigned certifies, pursuant to 18 U.S.C. Section 1350, as added bySection 906 of the Sarbanes-Oxley Act of 2002, that:

a)              The Report fullycomplies with the requirements of Section 13(a) or 15(d) of the SecuritiesExchange Act of 1934; and

b)             The informationcontained in the Report fairly presents, in all material respects, thefinancial condition and results of operations of the Registrant as of and for theperiod covered by the Report.
| Date:  |   | February 28, 2007 |   | /s/ Sherri R. Billings                      |
|--------|--------|-------------------|--------|---------------------------------------------|
|   |   |              |   | Sherri R. Billings  Chief Financial Officer |

 

----
UNITED STATES DISTRICT COURT

IN THE EASTERN DISTRICT OF MICHIGAN -- SOUTHERN DIVISION

STEVEN FORD,

Plaintiff,

Case No. 4:14-CV-13832

-vs- Hon. Marianne O. Battani

Magistrate Judge: R. Steven Whalen

DATAQUICK INFORMATION SYSTEMS, INC.,

Defendant.

JOINT NOTICE OF SETTLEMENT BETWEEN PLAINTIFF AND

DATAQUICK INFORMATION SYSTEMS, INC.

PLEASE TAKE NOTICE that all matters herein have been compromised and

settled as between Plaintiff Steven Ford (“Plaintiff”) and Defendant DataQuick

Information Systems, Inc., (“DataQuick”). Plaintiff and DataQuick will shortly

submit a proposed Stipulation and Order Of Dismissal, once the settlement has been

reduced to writing.

Respectfully Submitted,

By: s/ Amanda M. Longendyke

Amanda M. Longendyke (P-77777)

LYNGKLIP & ASSOCIATES

CONSUMER LAW CENTER, PLC

Attorney For Steven Ford 

24500 Northwestern Highway, Ste. 206

Southfield, MI 48075

PH: (248) 208-8864

Amanda@MichiganConsumerLaw.Com

2:14-cv-13832-MOB-RSW Doc # 63 Filed 07/23/15 Pg 1 of 3 Pg ID 582
By: s/ Stephen A. Weigand (With Consent)

Stephen A. Weigand (OH Bar No. 0083573)

Ronald I. Raether, Jr. (OH Bar No. 0667731)

Laura A. Sanom (P-58603)

FARUKI IRELAND & COX P.L.L.

Attorneys for DataQuick Information

Systems, Inc.

500 Courthouse Plaza, S.W.

10 North Ludlow Street

Dayton, OH 45402

PH: 937-227-3700

sweigand@ficlaw.com

rraether@ficlaw.com

lsanom@ficlaw.com

Local Address:

568 Lakeland Avenue

Grosse Pointe, MI 48230

Dated: July 23, 2015

2:14-cv-13832-MOB-RSW Doc # 63 Filed 07/23/15 Pg 2 of 3 Pg ID 583
Certificate of Service

I hereby certify that on July 23, 2015, I electronically filed the foregoing

document with the Clerk of the Court using the CM/ECF system, which will send

notification of such filing to all interested parties of record. 

Respectfully Submitted,

By: s/ Amanda M. Longendyke

Amanda M. Longendyke (P-77777)

LYNGKLIP & ASSOCIATES

CONSUMER LAW CENTER, PLC

Attorney For Steven Ford 

24500 Northwestern Highway, Ste. 206

Southfield, MI 48075

PH: (248) 208-8864

Amanda@MichiganConsumerLaw.Com

Dated: July 23, 2015

2:14-cv-13832-MOB-RSW Doc # 63 Filed 07/23/15 Pg 3 of 3 Pg ID 584
Editorial Note on Part 151
Editorial Note: Nomenclature changes to part 151 appear by USCG-2009-0702, 74 FR 49236, Sept. 25, 2009, and USCG-2012-0832, 77 FR 59784, Oct. 1, 2012.

§ 151.45-1 General. ( a ) Barges certificated as tank barges (Subchapter D of this chapter) or cargo barges (Subchapter I of this chapter) for the carriage of cargoes regulated by this subchapter shall meet all applicable requirements for operations in the appropriate subchapter; in addition, requirements prescribed in this subpart shall apply to either type of certification.
( b ) [Reserved]