Document Headings

                    Document headings vary by document type but may contain                    the following:                  
                -                       the agency or agencies that issued and signed a document                    
                -                       the number of the CFR title and the number of each part                      the document amends, proposes to amend, or is directly                      related to                    
                -                       the agency docket number / agency internal file number                    
                -                       the RIN which identifies each regulatory action listed in                      the Unified Agenda of Federal Regulatory and Deregulatory                      Actions                    

                    See the                                          Document Drafting Handbook                                        for more details.                  

###### Department of Transportation

###### Pipeline and Hazardous Materials Safety Administration 

          - [Docket No. PHMSA-06-25735; Notice 2] 

# AGENCY:

Pipeline and Hazardous Materials Safety Administration (PHMSA); U.S. Department of Transportation. 

# ACTION:

Grant of waiver; Sabine Pass LNG, L.P. 

# SUMMARY:

Sabine Pass LNG, L.P. (SPLNG) requested a waiver of compliance from the Federal pipeline safety regulation that requires liquefied natural gas (LNG) facilities constructed after March 31, 2000 to comply with the National Fire Protection Association's Standard 59A (NFPA 59A), 2001 Edition. The waiver specifically requested permission to use ultrasonic examination as an acceptable alternative non-destructive testing method for welds on LNG tanks. 

# SUPPLEMENTARY INFORMATION:

## Background 

                    SPLNG requested a waiver from compliance of the Federal pipeline safety requirements at 49 CFR 193.2301 for its facility at Cameron Parish, Louisiana. This regulation requires each LNG facility constructed after March 31, 2000 to comply with 49 CFR part 193 and NFPA Standard 59A, 2001 Edition. NFPA Standard 59A, 2001 Edition requires that welded containers designed for not more than 15 pounds per square inch gauge comply with the Eighth Edition, 1990, of American Petroleum Institute Standard 620 (API 620), “                    *Design and Construction of Large, Welded, Low-Pressure Storage Tanks (Appendix Q).*                    ” The Eighth Edition of API 620 requires inspection according to Appendix Q which calls for a full radiographic examination of all vertical and horizontal butt welds associated with the container.                 

SPLNG is proposing to use the Tenth Edition, 2002, Addendum 1 of the 2004 Edition of API 620 at its Cameron Parish LNG facility. This Tenth Edition allows ultrasonic examination as well as radiography as an acceptable alternative non-destructive testing method. SPLNG proposes to use ultrasonic examination, which consists of full semi-automated and manual ultrasonic examination using shear wave probes. The examination will also consist of a volumetric ultrasonic examination using a combination of creep wave probes and focused angled longitudinal wave probes. To allow ultrasonic examination in accordance with the most recent NFPA Standard 59A, 2006 Edition, a waiver is required. 

                    PHMSA considered SPLNG's waiver request and published a notice in the                     **Federal Register**                     inviting interested persons to comment on whether a waiver should be granted (71 FR 56584; September 27, 2006). No comments were received.                 

The NFPA issued a Tentative Interim Amendment to NFPA Standard 59A, 2006 Edition, effective February 14, 2006 (59A TIA06). This amendment incorporates API 620, Tenth Edition, 2002, Addendum 1, 2004. The Tenth Edition adds ultrasonic examination as an acceptable method of non-destructive examination for welds. The proposed wording of the Tenth Edition 2002, Addendum 1, 2004 of API 620 deletes “radiographic” inspection and replaces it with “complete” examination and defines “complete” examination as radiographic or ultrasonic examination. 

*Decision:*                     PHMSA finds that the use of ultrasonic examination in accordance with NFPA Standard 59A, 2006 Edition and 59A TIA06 is not inconsistent with pipeline safety and achieves an equivalent level of safety. Therefore, SPLNG's request for waiver of compliance with § 193.2301 is granted, subject to the following conditions: (1)                           ( print page 17220)                        Ultrasonic examinations of welds on metal containers shall comply with section 7.3.1.2 of NFPA Standard 59A, 2006 Edition and 59A TIA06; (2) the owner/operator shall retain all ultrasonic examination records for the life of the facility and these records shall be retained in a manner so they may not be altered; and (3) the interval for verifying the examination of welds against a calibration standard shall be eight hours or less. If the ultrasonic equipment is found to be out of calibration, all previous weld examinations determined by the operator shall be reexamined by ultrasonic equipment within a week.                 

Issued in Washington, DC on April 2, 2007. 

Jeffrey D. Wiese, 

Acting Associate Administrator for Pipeline Safety. 

[FR Doc. 07-1706 Filed 4-2-07; 4:52 pm] 

BILLING CODE 4910-60-P