Facility _Information

facility _id utility

_code legal_owner_nam e

legl_operator_name

legal_address_type

legal_address

legal_city legal_state legal_zip 2824 7570 Great River Energy Great River Energy

legal owner12300 ElmCreek Boulevard Maple Grove

MN 55369-4718

Page 1Facility _Information

plant_nam e

physical_address

phyical_city

physical_state

physical_zip

mailing_address

mailing_city

mailing_state

mailing_zip Stanton 4001 Highway 200A Stanton ND 58571-9402 4001 Highway

200A Stanton ND 58571-9402

Page 2Facility _Information

RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas No TRUE TRUE FALSE FALSE FALSE TRUE TRUE FALSE

Page 3Facility _Information

ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE FALSE State Reporting at time of tests and in semiannual and annual reports No Clean Air Markets Division Unit 1 MWgross summer is 132Unit 1 MWnet summer is 123Unit 1 design steam pressure is 1875Unit 1 operating steam pressure is 1807Unit 1 operatting steam temperature is 985Unit 1 design RH temp is 1005Unit 1 operating RH temp is 995Unit 10 gross is 60 MW Unit 10 net is 55 MW Unit 10 design steam pressure is 1965Unit 10 operating steam pressure is 1841Unit 10 operating steam temp is 968Unit 10 design RH temp is 1005Unit 10 operating RH temp is 983configuration orderu1 or unit 1 is a multistack or duct unitUnits 1 and 10 do not have post comubstion NOx controlsUnit 1 does not have SO2 controls10/13/2005 testing esp1a from 1029 to 1553Fuel Shipment Information incorrectly lists units as missing for shipment 388375. Units were correctly completed.Fuel Shipment Information incorrectly lists units as missing for shipment 564712. Units were correctly completed.Unit 10 has a 99% reduction of PM one hour averageUnit 10 has a 70% r

Page 4Facility _Information

Unit 1 MWgross summer is 132Unit 1 MWnet summer is 123Unit 1 design steam pressure is 1875Unit 1 operating steam pressure is 1807Unit 1 operatting steam temperature is 985Unit 1 design RH temp is 1005Unit 1 operating RH temp is 995Unit 10 gross is 60 MW Unit 10 net is 55 MW Unit 10 design steam pressure is 1965Unit 10 operating steam pressure is 1841Unit 10 operating steam temp is 968Unit 10 design RH temp is 1005Unit 10 operating RH temp is 983configuration orderu1 or unit 1 is a multistack or duct unitUnits 1 and 10 do not have post comubstion NOx controlsUnit 1 does not have SO2 controls10/13/2005 testing esp1a from 1029 to 1553Fuel Shipment Information incorrectly lists units as missing for shipment 388375. Units were correctly completed.Fuel Shipment Information incorrectly lists units as missing for shipment 564712. Units were correctly completed.Unit 10 has a 99% reduction of PM one hour averageUnit 10 has a 70% r

Page 5Facility _Information

Unit 1 MWgross summer is 132Unit 1 MWnet summer is 123Unit 1 design steam pressure is 1875Unit 1 operating steam pressure is 1807Unit 1 operatting steam temperature is 985Unit 1 design RH temp is 1005Unit 1 operating RH temp is 995Unit 10 gross is 60 MW Unit 10 net is 55 MW Unit 10 design steam pressure is 1965Unit 10 operating steam pressure is 1841Unit 10 operating steam temp is 968Unit 10 design RH temp is 1005Unit 10 operating RH temp is 983configuration orderu1 or unit 1 is a multistack or duct unitUnits 1 and 10 do not have post comubstion NOx controlsUnit 1 does not have SO2 controls10/13/2005 testing esp1a from 1029 to 1553Fuel Shipment Information incorrectly lists units as missing for shipment 388375. Units were correctly completed.Fuel Shipment Information incorrectly lists units as missing for shipment 564712. Units were correctly completed.Unit 10 has a 99% reduction of PM one hour averageUnit 10 has a 70% r

Page 6Facility _Information

Unit 1 MWgross summer is 132Unit 1 MWnet summer is 123Unit 1 design steam pressure is 1875Unit 1 operating steam pressure is 1807Unit 1 operatting steam temperature is 985Unit 1 design RH temp is 1005Unit 1 operating RH temp is 995Unit 10 gross is 60 MW Unit 10 net is 55 MW Unit 10 design steam pressure is 1965Unit 10 operating steam pressure is 1841Unit 10 operating steam temp is 968Unit 10 design RH temp is 1005Unit 10 operating RH temp is 983configuration orderu1 or unit 1 is a multistack or duct unitUnits 1 and 10 do not have post comubstion NOx controlsUnit 1 does not have SO2 controls10/13/2005 testing esp1a from 1029 to 1553Fuel Shipment Information incorrectly lists units as missing for shipment 388375. Units were correctly completed.Fuel Shipment Information incorrectly lists units as missing for shipment 564712. Units were correctly completed.Unit 10 has a 99% reduction of PM one hour averageUnit 10 has a 70% r

Page 7Facility _Information

Unit 1 MWgross summer is 132Unit 1 MWnet summer is 123Unit 1 design steam pressure is 1875Unit 1 operating steam pressure is 1807Unit 1 operatting steam temperature is 985Unit 1 design RH temp is 1005Unit 1 operating RH temp is 995Unit 10 gross is 60 MW Unit 10 net is 55 MW Unit 10 design steam pressure is 1965Unit 10 operating steam pressure is 1841Unit 10 operating steam temp is 968Unit 10 design RH temp is 1005Unit 10 operating RH temp is 983configuration orderu1 or unit 1 is a multistack or duct unitUnits 1 and 10 do not have post comubstion NOx controlsUnit 1 does not have SO2 controls10/13/2005 testing esp1a from 1029 to 1553Fuel Shipment Information incorrectly lists units as missing for shipment 388375. Units were correctly completed.Fuel Shipment Information incorrectly lists units as missing for shipment 564712. Units were correctly completed.Unit 10 has a 99% reduction of PM one hour averageUnit 10 has a 70% r

Page 8Facility _Information

Unit 1 MWgross summer is 132Unit 1 MWnet summer is 123Unit 1 design steam pressure is 1875Unit 1 operating steam pressure is 1807Unit 1 operatting steam temperature is 985Unit 1 design RH temp is 1005Unit 1 operating RH temp is 995Unit 10 gross is 60 MW Unit 10 net is 55 MW Unit 10 design steam pressure is 1965Unit 10 operating steam pressure is 1841Unit 10 operating steam temp is 968Unit 10 design RH temp is 1005Unit 10 operating RH temp is 983configuration orderu1 or unit 1 is a multistack or duct unitUnits 1 and 10 do not have post comubstion NOx controlsUnit 1 does not have SO2 controls10/13/2005 testing esp1a from 1029 to 1553Fuel Shipment Information incorrectly lists units as missing for shipment 388375. Units were correctly completed.Fuel Shipment Information incorrectly lists units as missing for shipment 564712. Units were correctly completed.Unit 10 has a 99% reduction of PM one hour averageUnit 10 has a 70% r

Page 9Facility _Information

Unit 1 MWgross summer is 132Unit 1 MWnet summer is 123Unit 1 design steam pressure is 1875Unit 1 operating steam pressure is 1807Unit 1 operatting steam temperature is 985Unit 1 design RH temp is 1005Unit 1 operating RH temp is 995Unit 10 gross is 60 MW Unit 10 net is 55 MW Unit 10 design steam pressure is 1965Unit 10 operating steam pressure is 1841Unit 10 operating steam temp is 968Unit 10 design RH temp is 1005Unit 10 operating RH temp is 983configuration orderu1 or unit 1 is a multistack or duct unitUnits 1 and 10 do not have post comubstion NOx controlsUnit 1 does not have SO2 controls10/13/2005 testing esp1a from 1029 to 1553Fuel Shipment Information incorrectly lists units as missing for shipment 388375. Units were correctly completed.Fuel Shipment Information incorrectly lists units as missing for shipment 564712. Units were correctly completed.Unit 10 has a 99% reduction of PM one hour averageUnit 10 has a 70% r

Page 10Facility _Information

Unit 1 MWgross summer is 132Unit 1 MWnet summer is 123Unit 1 design steam pressure is 1875Unit 1 operating steam pressure is 1807Unit 1 operatting steam temperature is 985Unit 1 design RH temp is 1005Unit 1 operating RH temp is 995Unit 10 gross is 60 MW Unit 10 net is 55 MW Unit 10 design steam pressure is 1965Unit 10 operating steam pressure is 1841Unit 10 operating steam temp is 968Unit 10 design RH temp is 1005Unit 10 operating RH temp is 983configuration orderu1 or unit 1 is a multistack or duct unitUnits 1 and 10 do not have post comubstion NOx controlsUnit 1 does not have SO2 controls10/13/2005 testing esp1a from 1029 to 1553Fuel Shipment Information incorrectly lists units as missing for shipment 388375. Units were correctly completed.Fuel Shipment Information incorrectly lists units as missing for shipment 564712. Units were correctly completed.Unit 10 has a 99% reduction of PM one hour averageUnit 10 has a 70% r

Page 11Facility _Information

Unit 1 MWgross summer is 132Unit 1 MWnet summer is 123Unit 1 design steam pressure is 1875Unit 1 operating steam pressure is 1807Unit 1 operatting steam temperature is 985Unit 1 design RH temp is 1005Unit 1 operating RH temp is 995Unit 10 gross is 60 MW Unit 10 net is 55 MW Unit 10 design steam pressure is 1965Unit 10 operating steam pressure is 1841Unit 10 operating steam temp is 968Unit 10 design RH temp is 1005Unit 10 operating RH temp is 983configuration orderu1 or unit 1 is a multistack or duct unitUnits 1 and 10 do not have post comubstion NOx controlsUnit 1 does not have SO2 controls10/13/2005 testing esp1a from 1029 to 1553Fuel Shipment Information incorrectly lists units as missing for shipment 388375. Units were correctly completed.Fuel Shipment Information incorrectly lists units as missing for shipment 564712. Units were correctly completed.Unit 10 has a 99% reduction of PM one hour averageUnit 10 has a 70% r

Page 12Facility _Information

Unit 1 MWgross summer is 132Unit 1 MWnet summer is 123Unit 1 design steam pressure is 1875Unit 1 operating steam pressure is 1807Unit 1 operatting steam temperature is 985Unit 1 design RH temp is 1005Unit 1 operating RH temp is 995Unit 10 gross is 60 MW Unit 10 net is 55 MW Unit 10 design steam pressure is 1965Unit 10 operating steam pressure is 1841Unit 10 operating steam temp is 968Unit 10 design RH temp is 1005Unit 10 operating RH temp is 983configuration orderu1 or unit 1 is a multistack or duct unitUnits 1 and 10 do not have post comubstion NOx controlsUnit 1 does not have SO2 controls10/13/2005 testing esp1a from 1029 to 1553Fuel Shipment Information incorrectly lists units as missing for shipment 388375. Units were correctly completed.Fuel Shipment Information incorrectly lists units as missing for shipment 564712. Units were correctly completed.Unit 10 has a 99% reduction of PM one hour averageUnit 10 has a 70% r

Page 13Facility _Information

Unit 1 MWgross summer is 132Unit 1 MWnet summer is 123Unit 1 design steam pressure is 1875Unit 1 operating steam pressure is 1807Unit 1 operatting steam temperature is 985Unit 1 design RH temp is 1005Unit 1 operating RH temp is 995Unit 10 gross is 60 MW Unit 10 net is 55 MW Unit 10 design steam pressure is 1965Unit 10 operating steam pressure is 1841Unit 10 operating steam temp is 968Unit 10 design RH temp is 1005Unit 10 operating RH temp is 983configuration orderu1 or unit 1 is a multistack or duct unitUnits 1 and 10 do not have post comubstion NOx controlsUnit 1 does not have SO2 controls10/13/2005 testing esp1a from 1029 to 1553Fuel Shipment Information incorrectly lists units as missing for shipment 388375. Units were correctly completed.Fuel Shipment Information incorrectly lists units as missing for shipment 564712. Units were correctly completed.Unit 10 has a 99% reduction of PM one hour averageUnit 10 has a 70% r

Page 14Facility _Information

Unit 1 MWgross summer is 132Unit 1 MWnet summer is 123Unit 1 design steam pressure is 1875Unit 1 operating steam pressure is 1807Unit 1 operatting steam temperature is 985Unit 1 design RH temp is 1005Unit 1 operating RH temp is 995Unit 10 gross is 60 MW Unit 10 net is 55 MW Unit 10 design steam pressure is 1965Unit 10 operating steam pressure is 1841Unit 10 operating steam temp is 968Unit 10 design RH temp is 1005Unit 10 operating RH temp is 983configuration orderu1 or unit 1 is a multistack or duct unitUnits 1 and 10 do not have post comubstion NOx controlsUnit 1 does not have SO2 controls10/13/2005 testing esp1a from 1029 to 1553Fuel Shipment Information incorrectly lists units as missing for shipment 388375. Units were correctly completed.Fuel Shipment Information incorrectly lists units as missing for shipment 564712. Units were correctly completed.Unit 10 has a 99% reduction of PM one hour averageUnit 10 has a 70% r

Page 15facility _contacts

facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 2824 1 Senior Generation Engineer Steve Smokey

7017455204 ssmokey@grenergy.com TRUE 2824 2 Manager, Environmental Services Mary Jo Roth 7634455212 mjroth@grenergy.com FALSE

Page 16facility _coal_utilized

facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note 2824 subbituminous 100 100

Page 17facility _oil_utilized

facility _id oil_type percentage_volume percentage_btu

other_type 2824 No.2 Fuel Oil (distillate) 100 100

Page 18facility _other_materials

facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain

Page 19facility _other_materials

rcra_explain

Page 20boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuelheat_input max_heat_input MWe_capacity 2824 1 Wall firing - front firing Dry Bottom coal 1800 1800 0 2824 10 Tangential firing Dry Bottom coal 642 642 0

Page 21boiler_information

MWe_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 0 83.4 81.7 0 0 1005 0 FALSE 0 0 82.8 81.8 0 0 1005 0 FALSE 0

Page 22boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 0 8206 94 N 2027 FALSE FALSE 0 7944 91 Subpart Da(1) 2027 FALSE

Page 23boiler_information

NOx_control

SO2_control

combustion_additives Yes No No Yes No No

Page 24boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 2824 1 coal - subbituminous 2007 99.9 99.9 2824 1 coal - subbituminous 2008 99.9 99.9 2824 1 coal - subbituminous 2009 99.9 99.9 2824 1 oil - distillate 2007 0.1 0.1 2824 1 oil - distillate 2008 0.1 0.1 2824 1 oil - distillate 2009 0.1 0.1 2824 10 coal - subbituminous 2007 99.9 99.9 2824 10 coal - subbituminous 2008 99.9 99.9 2824 10 coal - subbituminous 2009 99.9 99.9 2824 10 oil - distillate 2007 0.1 0.1 2824 10 oil - distillate 2008 0.1 0.1 2824 10 oil - distillate 2009 0.1 0.1

Page 25boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online 2824 1 Low NOx Burner 6/1/1999 2824 10 Low NOx Burner 6/1/1982 2824 10 Overfire Air 6/1/1982

Page 26boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online

Page 27boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 28facility _units

facility _id unit_id 2824 1 2824 10

Page 29unit_boilers

facility _id unit_id boiler_id 2824 1 1 2824 10 10

Page 30facility _controls

facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 2824 bag1 PM control Fabric Filter, reverse air FALSE 1/1/2000 2824 esp1 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 1/1/2000 2824 esp2 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 1/1/2000 2824 scrb10 SO2 control Spray dryer type FALSE 1/1/2000

Page 31facility _controls

reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive

Lim e NO

Page 32facility _sampling_ports

facility _id sampling_port_id 2824 bag10 2824 esp1a 2824 esp2b

Page 33facility _stacks

facility _id stack_id stack_height stack_diameter

sack_gas_velocity 2824 stack1 254

Page 34configurations

facility _id configuration_id 2824 u1 2824 u10

Page 35configuration_components

facility _id configuration_id

component_id

order component_type port_near 2824 u1 1 1 Unit 2824 u1 esp1 2 PM control 2824 u1 esp1a 3 Sam pling Port pevious 2824 u1 esp2 4 PM control 2824 u1 esp2b 5 Sam pling Port pevious 2824 u1 stack1 6 Stack 2824 u10 10 1 Unit 2824 u10 bag1 3 PM control 2824 u10 bag10 4 Sam pling Port next 2824 u10 scrb10 2 SO2 control 2824 u10 stack1 5 Stack

Page 36configuration_pollutants1

facility _id configuration_id

pollutant_nam e

permit_type_1

em lim it_1 em lim it_units_1 avg_period_1

em lim it_2 em lim it_units_2 2824 u1 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

1 hour 2824 u1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

3 pound per million British Thermal Unit (lb/MMBtu)

3 hours 2824 u1 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.46 pound per million British Thermal Unit (lb/MMBtu)

30 days 2824 u10 PM (Filterable) Fderal - Title V Operating Permit

0.03 pound per million British Thermal Unit (lb/MMBtu)

1 hour 2824 u10 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

0.6 pound per million British Thermal Unit (lb/MMBtu)

30 days 2824 u10 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.5 pound per million British Thermal Unit (lb/MMBtu)

30 days 0.4 pound per million British Thermal Unit (lb/MMBtu)

Page 37configuration_pollutants1

avg_period_2

em lim it_3 em lim it_units_3 avg_period_3

em lim it_4 em lim it_units_4 avg_period_4

em lim it_details

test_method 17

17

30 days

Page 38configuration_pollutants1

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping

req_reporting 0.1 pound per million British Thermal Unit (lb/MMBtu)

No CAM TitleV Quarterly 3 pound per million British Thermal Unit (lb/MMBtu)

No CEM TitleV Quarterly 0.46 pound per million British Thermal Unit (lb/MMBtu)

No CEM TitleV Quarterly 0.03 pound per million British Thermal Unit (lb/MMBtu)

No CAM Title V Quarterly 0.6 pound per million British Thermal Unit (lb/MMBtu)

No CEM Title V Quarterly 0.4 pound per million British Thermal Unit (lb/MMBtu)

No CEM Title V Quarterly

Page 39control_technologies

facility _id configuration_id

component_id

control_id project_titleproject_type vendor_name

vndor_contact

vendor_phone

Page 40control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 41control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 42control_technologies

feed_rate_units

Page 43control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 44control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_nam e

Page 45control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investm ent

total_operating_costs

base_year

Page 46control_costs

CBI

Page 47misc_controls

facility _id misc_control_id

control_description

Page 48misc_control_configurations

facility _id misc_control_id

configuration_id

Page 49fuel_shipments

facility _id shipment_id

shipment_date

amount_received

amount_units

fuel_type state_country other_country

county 2824 206077 5/1/2009 11004 short tons (2000 lbs) coal MT MT - Big Horn 2824 212896 5/1/2009 10633 short tons (2000 lbs) coal MT MT - Big Horn 2824 263232 11/1/2009 10926 short tons (2000 lbs) coal MT MT - Big Horn 2824 265812 11/1/2009 11003 short tons (2000 lbs) coal MT MT - Big Horn 2824 269744 10/1/2009 10990 short tons (2000 lbs) coal MT MT - Big Horn 2824 276788 10/1/2009 10997 short tons (2000 lbs) coal MT MT - Big Horn 2824 286066 12/1/2009 10900 short tons (2000 lbs) coal MT MT - Big Horn 2824 287391 9/1/2009 11090 short tons (2000 lbs) coal MT MT - Big Horn 2824 287840 11/1/2009 10721 short tons (2000 lbs) coal MT MT - Big Horn 2824 291871 9/1/2009 10996 short tons (2000 lbs) coal MT MT - Big Horn 2824 293048 12/1/2009 10489 short tons (2000 lbs) coal MT MT - Big Horn 2824 308410 11/1/2009 11005 short tons (2000 lbs) coal MT MT - Big Horn 2824 388375 5/1/2009 10448 short tons (2000 lbs) coal MT MT - Big Horn 2824 404982 7/1/2009 10391 short tons (2000 lbs) coal MT MT - Big Horn 2824 433884 11/1/2009 10995 short tons (2000 lbs) coal MT MT - Big Horn 2824 441218 11/1/2009 10909 short tons (2000 lbs) coal MT MT - Big Horn 2824 485857 5/1/2009 10374 short tons (2000 lbs) coal MT MT - Big Horn 2824 489391 7/1/2009 10931 short tons (2000 lbs) coal MT MT - Big Horn 2824 494157 7/1/2009 10651 short tons (2000 lbs) coal MT MT - Big Horn 2824 498571 6/1/2009 10121 short tons (2000 lbs) coal MT MT - Big Horn 2824 500722 7/1/2009 10460 short tons (2000 lbs) coal MT MT - Big Horn 2824 504378 6/1/2009 10175 short tons (2000 lbs) coal MT MT - Big Horn 2824 509994 6/1/2009 10631 short tons (2000 lbs) coal MT MT - Big Horn 2824 514240 6/1/2009 10705 short tons (2000 lbs) coal MT MT - Big Horn 2824 534165 3/1/2009 9465 short tons (2000 lbs) coal MT MT - Big Horn 2824 541194 3/1/2009 9690 short tons (2000 lbs) coal MT MT - Big Horn 2824 546560 3/1/2009 9173 short tons (2000 lbs) coal MT MT - Big Horn 2824 548977 2/1/2009 10085 short tons (2000 lbs) coal MT MT - Big Horn 2824 555425 2/1/2009 9829 short tons (2000 lbs) coal MT MT - Big Horn 2824 557933 5/1/2009 11080 short tons (2000 lbs) coal MT MT - Big Horn 2824 564712 5/1/2009 11062 short tons (2000 lbs) coal MT MT - Big Horn 2824 596463 4/1/2009 11047 short tons (2000 lbs) coal MT MT - Big Horn 2824 600730 4/1/2009 11003 short tons (2000 lbs) coal MT MT - Big Horn 2824 603204 1/1/2009 10547 short tons (2000 lbs) coal MT MT - Big Horn 2824 621158 6/1/2009 11077 short tons (2000 lbs) coal MT MT - Big Horn 2824 628640 7/1/2009 11034 short tons (2000 lbs) coal MT MT - Big Horn 2824 640132 1/1/2009 10127 short tons (2000 lbs) coal MT MT - Big Horn 2824 641360 8/1/2009 10901 short tons (2000 lbs) coal MT MT - Big Horn 2824 652263 1/1/2009 9772 short tons (2000 lbs) coal MT MT - Big Horn 2824 657130 2/1/2009 9626 short tons (2000 lbs) coal MT MT - Big Horn 2824 682852 7/1/2009 11100 short tons (2000 lbs) coal MT MT - Big Horn 2824 688252 8/1/2009 10984 short tons (2000 lbs) coal MT MT - Big Horn 2824 688888 1/1/2009 10230 short tons (2000 lbs) coal MT MT - Big Horn 2824 696771 3/1/2009 9616 short tons (2000 lbs) coal MT MT - Big Horn 2824 701342 1/1/2009 10379 short tons (2000 lbs) coal MT MT - Big Horn 2824 704788 4/1/2009 9792 short tons (2000 lbs) coal MT MT - Big Horn 2824 710612 4/1/2009 10044 short tons (2000 lbs) coal MT MT - Big Horn 2824 714022 4/1/2009 10150 short tons (2000 lbs) coal MT MT - Big Horn 2824 734608 3/1/2009 9456 short tons (2000 lbs) coal MT MT - Big Horn 2824 741881 3/1/2009 9850 short tons (2000 lbs) coal MT MT - Big Horn

Page 50fuel_shipments

coal_seam shipment_method Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train Anderson Dietz

Unit Train

Page 51fuel_shipment_configurations

facility _id shipment_id

configuration_id 2824 206077 u1 2824 206077 u10 2824 212896 u1 2824 212896 u10 2824 263232 u1 2824 263232 u10 2824 265812 u1 2824 265812 u10 2824 269744 u1 2824 269744 u10 2824 276788 u1 2824 276788 u10 2824 286066 u1 2824 286066 u10 2824 287391 u1 2824 287391 u10 2824 287840 u1 2824 287840 u10 2824 291871 u1 2824 291871 u10 2824 293048 u1 2824 293048 u10 2824 308410 u1 2824 308410 u10 2824 388375 u1 2824 388375 u10 2824 404982 u1 2824 404982 u10 2824 433884 u1 2824 433884 u10 2824 441218 u1 2824 441218 u10 2824 485857 u1 2824 485857 u10 2824 489391 u1 2824 489391 u10 2824 494157 u1 2824 494157 u10 2824 498571 u1 2824 498571 u10 2824 500722 u1 2824 500722 u10 2824 504378 u1 2824 504378 u10 2824 509994 u1 2824 509994 u10 2824 514240 u1 2824 514240 u10 2824 534165 u1 2824 534165 u10 2824 541194 u1

Page 52fuel_shipment_configurations

2824 541194 u10 2824 546560 u1 2824 546560 u10 2824 548977 u1 2824 548977 u10 2824 555425 u1 2824 555425 u10 2824 557933 u1 2824 557933 u10 2824 564712 u1 2824 564712 u10 2824 596463 u1 2824 596463 u10 2824 600730 u1 2824 600730 u10 2824 603204 u1 2824 603204 u10 2824 621158 u1 2824 621158 u10 2824 628640 u1 2824 628640 u10 2824 640132 u1 2824 640132 u10 2824 641360 u1 2824 641360 u10 2824 652263 u1 2824 652263 u10 2824 657130 u1 2824 657130 u10 2824 682852 u1 2824 682852 u10 2824 688252 u1 2824 688252 u10 2824 688888 u1 2824 688888 u10 2824 696771 u1 2824 696771 u10 2824 701342 u1 2824 701342 u10 2824 704788 u1 2824 704788 u10 2824 710612 u1 2824 710612 u10 2824 714022 u1 2824 714022 u10 2824 734608 u1 2824 734608 u10 2824 741881 u1 2824 741881 u10

Page 53fuel_shipment_samples

facility _id shipment_id

sample_id amount_fuel amount_fuel_units

total_sulfur ash_content heating_value

hating_units 2824 206077 1 11004 tons 0.43 7.22 12237 Btu/lb 2824 212896 1 10633 tons 0.4 5.44 12501 Btu/lb 2824 263232 1 10926 tons 0.42 5.66 12446 Btu/lb 2824 265812 1 11003 tons 0.45 5.72 12427 Btu/lb 2824 269744 1 10990 tons 0.43 8.3 11962 Btu/lb 2824 276788 1 10997 tons 0.43 8.3 11962 Btu/lb 2824 286066 1 10900 tons 0.6 7.14 12261 Btu/lb 2824 287391 1 11090 tons 0.44 6.34 12334 Btu/lb 2824 287840 1 10721 tons 0.48 6.59 12313 Btu/lb 2824 291871 1 10996 tons 0.42 5.51 12443 Btu/lb 2824 293048 1 10489 tons 0.49 7.28 12163 Btu/lb 2824 308410 1 11005 tons 0.49 7.24 12157 Btu/lb 2824 388375 1 10448 tons 0.49 6.24 12274 Btu/lb 2824 404982 1 10391 tons 0.48 6.24 12300 Btu/lb 2824 433884 1 10995 tons 0.4 6.32 12299 Btu/lb 2824 441218 1 10909 tons 0.46 5.93 12350 Btu/lb 2824 485857 1 10374 tons 0.5 6.4 12180 Btu/lb 2824 489391 1 10931 tons 0.59 7.07 12340 Btu/lb 2824 494157 1 10651 tons 0.51 6.94 12283 Btu/lb 2824 498571 1 10121 tons 0.51 6.73 12258 Btu/lb 2824 500722 1 10460 tons 0.47 6.21 12248 Btu/lb 2824 504378 1 10175 tons 0.44 5.12 12433 Btu/lb 2824 509994 1 10631 tons 0.43 5.11 12433 Btu/lb 2824 514240 1 10705 tons 0.36 5.7 12362 Btu/lb 2824 534165 1 9465 tons 0.36 5.7 12362 Btu/lb 2824 541194 1 9690 tons 0.42 5.55 12390 Btu/lb 2824 546560 1 9173 tons 0.42 5.54 12390 Btu/lb 2824 548977 1 10085 tons 0.4 5.39 12398 Btu/lb 2824 555425 1 9829 tons 0.51 6.22 12323 Btu/lb 2824 557933 1 11080 tons 0.44 5.32 12438 Btu/lb 2824 564712 1 11062 tons 0.44 5.23 12380 Btu/lb 2824 596463 1 11047 tons 0.41 5.73 12375 Btu/lb 2824 600730 1 11003 tons 0.42 5.98 12351 Btu/lb 2824 603204 1 10547 tons 0.44 6 12353 Btu/lb 2824 621158 1 11077 tons 0.35 5.34 12438 Btu/lb 2824 628640 1 11034 tons 0.38 5.6 12398 Btu/lb 2824 640132 1 10127 tons 0.44 5.84 12362 Btu/lb 2824 641360 1 10901 tons 0.3 6.31 12287 Btu/lb 2824 652263 1 9772 tons 0.44 5.33 12474 Btu/lb 2824 657130 1 9626 tons 0.47 5.3 12510 Btu/lb 2824 682852 1 11100 tons 0.48 5.3 12416 Btu/lb 2824 688252 1 10984 tons 0.52 7.05 12250 Btu/lb 2824 688888 1 10230 tons 0.37 5.76 12383 Btu/lb 2824 696771 1 9616 tons 0.4 6.09 12364 Btu/lb 2824 701342 1 10379 tons 0.43 5.79 12521 Btu/lb 2824 704788 1 9792 tons 0.44 5.53 12529 Btu/lb 2824 710612 1 10044 tons 0.48 5.78 12486 Btu/lb 2824 714022 1 10150 tons 0.55 6.57 12351 Btu/lb 2824 734608 1 9456 tons 0.35 4.57 12597 Btu/lb 2824 741881 1 9850 tons 0.34 4.74 12508 Btu/lb

Page 54fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW standard operational procedures Other Great River Energy Coal Creek Station 2875 3rd St. SW

Page 55fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_nam e lab_address lab_city lab_state lab_zip analysis_copies Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes Underwood ND 58576 Great River Energy Coal Creek Station 2875 3rd St. SW

Underwood ND 58576 Yes

Page 56fuel_shipment_samples

analysis_copies

Page 57fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL 2824 206077 1 Mercury (Hg) 0.08 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 212896 1 Mercury (Hg) 0.08 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 263232 1 Mercury (Hg) 0.07 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 265812 1 Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 269744 1 Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 276788 1 Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 286066 1 Mercury (Hg) 0.07 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 287391 1 Mercury (Hg) 0.07 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 287840 1 Mercury (Hg) 0.07 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 291871 1 Mercury (Hg) 0.04 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 293048 1 Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 308410 1 Mercury (Hg) 0.08 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 388375 1 Mercury (Hg) 0.08 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 404982 1 Mercury (Hg) 0.08 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 433884 1 Mercury (Hg) 0.07 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 441218 1 Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 485857 1 Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 489391 1 Mercury (Hg) 0.6 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 494157 1 Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 498571 1 Mercury (Hg) 0.08 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 500722 1 Mercury (Hg) 0.08 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 504378 1 Mercury (Hg) 0.07 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 509994 1 Mercury (Hg) 0.07 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 514240 1 Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 534165 1 Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 541194 1 Mercury (Hg) 0.04 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 546560 1 Mercury (Hg) 0.4 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 548977 1 Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 555425 1 Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 557933 1 Mercury (Hg) 0.13 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 564712 1 Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 596463 1 Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 600730 1 Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 603204 1 Mercury (Hg) 0.08 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 621158 1 Mercury (Hg) 0.02 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 628640 1 Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 640132 1 Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 641360 1 Mercury (Hg) 0.02 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 652263 1 Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 657130 1 Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 682852 1 Mercury (Hg) 0.04 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 688252 1 Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 688888 1 Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 696771 1 Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 701342 1 Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 704788 1 Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 710612 1 Mercury (Hg) 0.07 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 714022 1 Mercury (Hg) 0.15 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 734608 1 Mercury (Hg) 0.04 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 741881 1 Mercury (Hg) 0.04 mi lligramper kilogram (dry) (mg/kg) FALSE

Page 58test_reports

facility _id report_id report_type other_type report_description report_begin_date

report_end_date

before_control

during_deviation 2824 2005 Mercury

Research other Research 2005 mercury emissions research testing using activated carbon. 7/12/2005 ######## Yes No 2824 2006 RATA A

compliance 2006 RATA in January 1/10/2006 1/11/2006 No No 2824 2006 RATA B

compliance RATA in October 8/16/2006 8/16/2006 No No 2824 2007 Mercury

Research other Research 2007 Mercury emissions control testing consisting of parametric tests and 60 day long term control test. 8/17/2007 ######## Yes No 2824 2009 Mercury

and Trace Metals other research Report not completed by tim e of ICR. Some data can be supplied. Testing on mercury controls of activated carbon and other trace elements. Mercury results provided in ICR. ######## 11/4/2009 Yes No 2824 MerCap testing

other Research testing Two year study

that ran from 2004 into 2006 of the MerCap mercury control system. PRB coal will be listed as the testing dates. 2/1/2005 5/12/2005 Yes No 2824 Particulate test

compliance Particulate Emission Compliance Test ######## ######## No No 2824 RATA 2005

compliance 2005 RATA 9/21/2005 9/23/2005 No No 2824 RATA 2007

compliance RATA for 2007 7/10/2007 7/11/2007 No No 2824 RATA 2008

compliance RATA testing in 2008 8/12/2008 8/13/2008 No No 2824 RATA 2009

compliance RATA testing for 2009 7/28/2009 7/28/2009 No No

Page 59test_reports

deviation_reports No No No No No No No No No No No

Page 60test_report_configurations

facility _id report_id configuration_id 2824 2005 Mercury

Research u1 2824 2006 RATA A

u1 2824 2006 RATA A

u10 2824 2006 RATA B

u1 2824 2006 RATA B

u10 2824 2007 Mercury

Research u1 2824 2009 Mercury

and Trace Metals u1 2824 2009 Mercury

and Trace Metals u10 2824 MerCap testing

u10 2824 Particulate test

u1 2824 Particulate test

u10 2824 RATA 2005u1 2824 RATA 2005u10 2824 RATA 2007u1 2824 RATA 2007u10 2824 RATA 2008u1 2824 RATA 2008u10 2824 RATA 2009u1 2824 RATA 2009u10

Page 61test_report_fuels

facility _id report_id fuel_id 2824 2005 Mercury

Research subbituminous 2824 2006 RATA A

subbituminous 2824 2006 RATA B

subbituminous 2824 2007 Mercury

Research subbituminous 2824 2009 Mercury

and Trace Metals subbituminous 2824 MerCap testing

subbituminous 2824 Particulate test

subbituminous 2824 RATA 2005

subbituminous 2824 RATA 2007

subbituminous 2824 RATA 2008

subbituminous 2824 RATA 2009

subbituminous

Page 62test_report_fuel_types

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 2824 2005 Mercury

Research subbituminous

coal - subbituminous

100 100 2824 2006 RATA A

subbituminous

coal - subbituminous

100 100 2824 2006 RATA B

subbituminous

coal - subbituminous

100 100 2824 2007 Mercury

Research subbituminous

coal - subbituminous

100 100 2824 2009 Mercury

and Trace Metals subbituminous

coal - subbituminous

100 100 2824 MerCap testing

subbituminous

coal - subbituminous

100 100 2824 Particulate test

subbituminous

coal - subbituminous

100 100 2824 RATA 2005

subbituminous

coal - subbituminous

100 100 2824 RATA 2007

subbituminous

coal - subbituminous

100 100 2824 RATA 2008

subbituminous

coal - subbituminous

100 100 2824 RATA 2009

subbituminous

coal - subbituminous

100 100

Page 63cem_data

facility _id tim e_period

cem_period_description 2824 All tim es All Part 75 required parameters for all operational hours.

Page 64cem_data_pollutants1

facility _id tim e_period

pollutant_nam e 2824 All tim es Nitrogen Oxide (NOx) 2824 All tim es Sulfur Dioxide (SO2)

Page 65test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_bypass_percent

testing_bypass_percent 2824 2005 Mercury

Research esp1a Yes A sampling port was installed inline with the activated carbon injection ports to determine upstream mercury concentrations No 2824 2006 RATA A

bag10 No No 2824 2006 RATA A

esp1a No No 2824 2006 RATA A

esp2b No No 2824 2006 RATA B

bag10 No No 2824 2006 RATA B

esp1a No No 2824 2006 RATA B

esp2b No No 2824 2007 Mercury

Research esp1a Yes In front of the ESP at the point of injection for inlet concentrations No 2824 2009 Mercury

and Trace Metals bag10 Yes Inlet to baghouse No 2824 2009 Mercury

and Trace Metals esp1a Yes Inlet to the ESP No 2824 MerCap testing

ba10 Yes Mercury gas samples were collected to the inlet of the baghouse. Mercury control device was located inside of the baghouse. No 2824 Particulate test

bag10 No No 2824 Particulate test

esp1a No No 2824 Particulate test

esp2b No No 2824 RATA 2005bag10 No No 2824 RATA 2005

esp1a No No 2824 RATA 2005

esp2b No No 2824 RATA 2007bag10 No No 2824 RATA 2007

esp1a No No 2824 RATA 2007

esp2b No No 2824 RATA 2008bag10 No No 2824 RATA 2008

esp1a No No 2824 RATA 2008

esp2b No No 2824 RATA 2009bag10 No No 2824 RATA 2009

esp1a No No 2824 RATA 2009

esp2b No No

Page 66test_report_sampling

fg_fraction 100% of the duct flow.

100 100 100 One of ten baghouse compartments were sampled, so 10% of flue gas.

100

Page 67sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetim e

unit_load net_generation fg_moisture_content 2824 2005 Mercury

Research esp1a 1 7/12/2005 7/15/2005 128 128 9.2 2824 2005 Mercury

Research esp1a 2 9/14/2005 9/19/2005 128 128 22 2824 2005 Mercury

Research esp1a 3 7/16/2005 7/19/2005 128 128 22 2824 2005 Mercury

Research esp1a 4 7/17/2005 7/17/2005 128 128 22 2824 2005 Mercury

Research esp1a 5 9/19/2005 ######## 128 128 22 2824 2005 Mercury

Research esp1a 6 ######## ######## 128 128 9.2 2824 2006 RATA A

bag10 average 1/12/2006 1/12/2006 55 55 15.8 2824 2006 RATA A

esp1a average 1/10/2006 1/10/2006 128 128 9.2 2824 2006 RATA A

esp2b average 1/11/2006 1/11/2006 128 128 9.52 2824 2006 RATA B

bag10 average 8/17/2006 8/17/2006 56 56 15.75 2824 2006 RATA B

esp1a average 8/16/2006 8/16/2006 128 128 9.2 2824 2006 RATA B

esp2b average 8/16/2006 8/16/2006 128 128 9.48 2824 2007 Mercury

Research esp1a 1 8/17/2007 8/17/2007 125 125 9.2 2824 2007 Mercury

Research esp1a 2 8/19/2007 8/19/2007 125 125 9.2 2824 2007 Mercury

Research esp1a 3 8/24/2007 8/24/2007 125 125 9.2 2824 2007 Mercury

Research esp1a 4 8/25/2007 8/25/2007 125 125 9.2 2824 2007 Mercury

Research esp1a 5 8/26/2007 8/26/2007 125 125 9.2 2824 2007 Mercury

Research esp1a 6 8/27/2007 8/27/2007 125 125 9.2 2824 2009 Mercury

and Trace Metals bag10 1 ######## 11/3/2009 58 58 15.75 2824 2009 Mercury

and Trace Metals bag10 2 ######## 11/4/2009 58 58 15.75 2824 2009 Mercury

and Trace Metals esp1a 1 11/3/2009 11/3/2009 124 124 9.2 2824 2009 Mercury

and Trace Metals esp1a 2 11/4/2009 11/4/2009 124 124 9.2 2824 MerCap testing

ba10 1 2/1/2005 2/1/2005 52 52 15.75 2824 MerCap testing

ba10 2 2/1/2005 2/1/2005 52 52 15.75 2824 MerCap testing

ba10 3 2/2/2005 2/2/2005 52 52 15.75 2824 MerCap testing

ba10 4 2/2/2005 2/2/2005 52 52 15.75 2824 MerCap testing

ba10 5 5/12/2005 5/12/2005 52 52 2824 MerCap testing

ba10 6 5/12/2005 5/12/2005 52 52 15.75 2824 Particulate test

bag10 average ######## ######## 60 60 15.75 2824 Particulate test

esp1a average ######## ######## 130 130 9.2 2824 Particulate test

esp2b average ######## ######## 130 130 15.75 2824 RATA 2005bag10 average 9/22/2005 9/22/2005 62 62 15.75 2824 RATA 2005

esp1a average 9/23/2005 9/23/2005 128 128 9.2 2824 RATA 2005

esp2b average 9/21/2005 9/21/2005 125 125 9.48 2824 RATA 2007bag10 average 7/11/2007 7/11/2007 54 54 15.75 2824 RATA 2007

esp1a average 7/10/2007 7/10/2007 125 125 9.2 2824 RATA 2007

esp2b average 7/10/2007 7/10/2007 125 125 9.48 2824 RATA 2008bag10 average 8/13/2008 8/13/2008 58 58 15.75 2824 RATA 2008

esp1a average 8/12/2008 8/12/2008 126 126 9.2 2824 RATA 2008

esp2b average 8/12/2008 8/12/2008 125 125 9.48 2824 RATA 2009bag10 average 7/29/2009 7/29/2009 56 56 9.2 2824 RATA 2009

esp1a average 7/28/2009 7/28/2009 129 129 9.2 2824 RATA 2009

esp2b average 7/28/2009 7/28/2009 129 129 9.2

Page 68sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 204358 dscfm 7.3 12.39 300 204000 dscfm 7.3 12.39 300 204000 dscfm 7.3 12.39 300 204000 dscfm 7.3 12.39 300 204000 dscfm 7.3 12.39 300 204000 dscfm 7.3 12.39 300 157400 dscfm 210 6.3 13.3 210 204000 dscfm 300 7.3 12.39 300 215000 dscfm 300 7.74 12 300 157787 dscfm 204 6.29 13.32 204 205000 dscfm 300 7.3 12.39 300 214841 dscfm 300 7.74 12.04 300 204000 dscfm 7.3 12.39 300 204000 dscfm 7.3 12.39 300 204000 dscfm 7.3 12.39 300 204000 dscfm 7.3 12.39 300 204000 dscfm 7.3 12.39 300 204000 dscfm 7.3 12.39 300 157000 dscfm 6.29 13.32 210 157000 dscfm 6.29 13.32 210 204000 dscfm 7.3 12.39 300 204000 dscfm 7.3 12.39 300 16000 dscfm 6.29 13.32 210 16000 dscfm 6.29 13.32 210 16000 dscfm 6.29 13.32 210 16000 dscfm 6.29 13.32 210 16000 dscfm 6.29 13.32 210 16000 dscfm 6.29 13.32 210 157387 dscfm 210 6.29 13.32 210 204358 dscfm 300 7.3 12.39 300 157387 dscfm 218 6.29 13.32 218 157387 dscfm 218 15.75 13.32 218 157387 dscfm 300 6.3 13.32 300 214841 dscfm 300 7.74 12.04 300 157387 dscfm 206 6.29 13.32 206 204358 dscfm 300 7.3 12.39 300 214841 dscfm 300 7.74 12.04 300 157387 dscfm 205 6.29 13.32 205 204358 dscfm 300 7.3 12.39 300 214841 dscfm 300 7.74 12.04 300 204358 dscfm 201 7.3 12.39 201 204360 dscfm 300 7.3 12.39 300 214841 dscfm 300 7.74 12.04 300

Page 69sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value EPRI CMM mercury

analy zer and Ontario Hydro method subbituminous 128 5.31 9600 EPRI CMM mercury

analy zer and Ontario Hydro method subbituminous 128 5.31 9600 EPRI CMM mercury

analy zer and Ontario Hydro method subbituminous 128 5.31 9600 EPRI CMM mercury

analy zer and Ontario Hydro method subbituminous 128 5.31 9600 EPRI CMM mercury

analy zer and Ontario Hydro method subbituminous 128 5.31 9600 EPRI CMM mercury

analy zer and Ontario Hydro method subbituminous 128 5.31 9600 6C subbituminous 55 4.6 9742 6C subbituminous 128 4.63 9344 subbituminous 128 4.63 9344 6C 7E subbituminous 56 4.63 9344 6C 7E subbituminous 128 4.63 9344 6C 7E subbituminous 128 4.63 9344 EPRI CMM mercury

analy zer and Ontario Hydro method subbituminous 125 4.58 9400 EPRI CMM mercury

analy zer and Ontario Hydro method subbituminous 125 4.58 9400 EPRI CMM mercury

analy zer and Ontario Hydro method subbituminous 125 4.58 9400 EPRI CMM mercury

analy zer and Ontario Hydro method subbituminous 125 4.58 9400 EPRI CMM mercury

analy zer and Ontario Hydro method subbituminous 125 4.58 9400 EPRI CMM mercury

analy zer and Ontario Hydro method subbituminous 125 4.58 9400 EPRI CMM mercury

analy zer and M29 subbituminous 58 6.02 12494 EPRI CMM mercury

analy zer and m29 subbituminous 58 6.02 12494 EPRI CMM mercury

analy zer and M29 subbituminous 124 124 5.01 12544 EPRI CMM mercury

analy zer and M29 subbituminous 124 5.01 12544 EPRI CMM mercury

analy zer and Ontario Hydro method and gold coupon measured at 3% O2

subbituminous 52 5.31 9600 EPRI CMM mercury

analy zer and Ontario Hydro method and gold coupon subbituminous 52 5.31 9600 EPRI CMM mercury

analy zer and Ontario Hydro method and gold coupon subbituminous 52 5.31 9600 EPRI CMM mercury

analy zer and Ontario Hydro method and gold coupon subbituminous 52 5.31 9600 EPRI CMM mercury

analy zer and Ontario Hydro method and gold coupon subbituminous 52 5.31 9600 EPRI CMM mercury

analy zer and Ontario Hydro method and gold coupon subbituminous 52 5.31 9600 Method 17 subbituminous 60 5.31 9304 Method 17 subbituminous 130 5.3 9304 Method 17 subbituminous 130 5.31 9304 Method 6C 7E subbituminous 60 5.31 9304 Method 6C 7E subbituminous 130 5.3 9304 Method 6C 7E subbituminous 125 5.31 9304 Methods 6C and 7E subbituminous 54 4.58 9352 Methods 6C and 7E subbituminous 125 4.58 9352

methods 6C 7E subbituminous 125 4.58 9352 Methods 6C and 7E subbituminous 58 4.77 9308 Methods 6C and 7E subbituminous 126 4.77 9308 Methods 6C and 7E subbituminous 125 6.47 9308 Methods 6C and 7E subbituminous 56 4.6 9380 Methods 6C and 7E subbituminous 129 4.6 9380 Methods 6C and 7E subbituminous 129 6.84 9380

Page 70sampling_runs

fuel_sulfur 0.27 0.27 0.27 0.27 0.27 0.27 0.32 0.32 0.32 0.32 0.32 0.32 0.3 0.3 0.3 0.3 0.3 0.3 0.45 0.45 0.32 0.32 0.27 0.27 0.27 0.27 0.27 0.27 0.32 0.32 0.32 0.32 0.32 0.32 0.33 0.33 0.33 0.36 0.36 0.36 0.35 0.35 0.35

Page 71sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_nam e conc conc_units conc_ND conc_MDL 2824 RATA 2005

esp2b average Nitrogen Oxide (NOx) 150 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2005bag10 average Nitrogen Oxide (NOx) 153 parts per million by volum e (dry) (ppmvd) FALSE 2824 2006 RATA A

esp1a average Sulfur Dioxide (SO2) 247 parts per million by volum e (dry) (ppmvd) FALSE 2824 2006 RATA A

esp1a average Nitrogen Oxide (NOx) 163 parts per million by volum e (dry) (ppmvd) FALSE 2824 2006 RATA A

esp2b average Sulfur Dioxide (SO2) 218 parts per million by volum e (dry) (ppmvd) FALSE 2824 2006 RATA A

esp2b average Nitrogen Oxide (NOx) 156 parts per million by volum e (dry) (ppmvd) FALSE 2824 2006 RATA A

bag10 average Sulfur Dioxide (SO2) 21 parts per million by

volum e (dry) (ppmvd) FALSE 2824 2006 RATA A

bag10 average Nitrogen Oxide (NOx) 152 parts per million by volum e (dry) (ppmvd @ 7% O2) FALSE 2824 2006 RATA B

esp1a average Sulfur Dioxide (SO2) 152 parts per million by volum e (dry) (ppmvd) FALSE 2824 2006 RATA B

esp1a average Nitrogen Oxide (NOx) 211 parts per million by volum e (dry) (ppmvd) FALSE 2824 2006 RATA B

esp2b average Sulfur Dioxide (SO2) 146 parts per million by volum e (dry) (ppmvd) FALSE 2824 2006 RATA B

esp2b average Nitrogen Oxide (NOx) 156 parts per million by volum e (dry) (ppmvd) FALSE 2824 2006 RATA B

bag10 average Nitrogen Oxide (NOx) 150 parts per million by volum e (dry) (ppmvd) FALSE 2824 2006 RATA B

bag10 average Sulfur Dioxide (SO2) 3.3 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2007

esp1a average Sulfur Dioxide (SO2) 250 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2007

esp1a average Nitrogen Oxide (NOx) 258 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2007

esp2b average Sulfur Dioxide (SO2) 262 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2007

esp2b average Nitrogen Oxide (NOx) 254 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2007bag10 average Sulfur Dioxide (SO2) 17 parts per million by

volum e (dry) (ppmvd) FALSE 2824 RATA 2007bag10 average Nitrogen Oxide (NOx) 257 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2008

esp1a average Sulfur Dioxide (SO2) 198 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2008

esp1a average Nitrogen Oxide (NOx) 152 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2008

esp2b average Sulfur Dioxide (SO2) 185 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2008

esp2b average Nitrogen Oxide (NOx) 159 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2008bag10 average Sulfur Dioxide (SO2) 20 parts per million by

volum e (dry) (ppmvd) FALSE 2824 RATA 2008bag10 average Nitrogen Oxide (NOx) 154 parts per million by volum e (dry) (ppmvd) FALSE 2824 MerCap testing

ba10 1 Total Mercury (Hgt) 5.37 microgram per dry standard cubic meter ( FALSE 2824 MerCap testing

ba10 2 Total Mercury (Hgt) 5.81 microgram per dry standard cubic meter ( FALSE 2824 MerCap testing

ba10 3 Total Mercury (Hgt) 6.27 microgram per dry standard cubic meter ( FALSE 2824 MerCap testing

ba10 4 Total Mercury (Hgt) 1.75 microgram per dry standard cubic meter ( FALSE 2824 MerCap testing

ba10 5 Total Mercury (Hgt) 8.38 microgram per dry standard cubic meter ( FALSE 2824 MerCap testing

ba10 6 Total Mercury (Hgt) 7.73 microgram per dry standard cubic meter ( FALSE 2824 2007 Mercury

Research esp1a 1 Total Mercury (Hgt) 5.26 microgram per normal cubic meter (

FALSE 2824 2007 Mercury

Research esp1a 2 Total Mercury (Hgt) 1 microgram per normal cubic meter ( FALSE 2824 2007 Mercury

Research esp1a 3 Total Mercury (Hgt) 3.2 microgram per normal cubic meter (

FALSE 2824 2007 Mercury

Research esp1a 4 Total Mercury (Hgt) 1.8 microgram per normal cubic meter (

FALSE 2824 2007 Mercury

Research esp1a 5 Total Mercury (Hgt) 2 microgram per normal cubic meter ( FALSE 2824 2007 Mercury

Research esp1a 6 Total Mercury (Hgt) 1.6 microgram per normal cubic meter (

FALSE 2824 2009 Mercury

and Trace Metals esp1a 1 Total Mercury (Hgt) 4.13 microgram per dry standard cubic meter ( FALSE 2824 2009 Mercury

and Trace Metals esp1a 2 Total Mercury (Hgt) 0.38 microgram per dry standard cubic meter ( FALSE 2824 2009 Mercury

and Trace Metals bag10 1 Total Mercury (Hgt) 6.89 microgram per dry standard cubic meter ( FALSE 2824 2009 Mercury

and Trace Metals bag10 2 Total Mercury (Hgt) 0.43 microgram per dry standard cubic meter ( FALSE 2824 Particulate test

esp1a average PM (Filterable) 239000 microgram per dry standard cubic meter ( FALSE 2824 Particulate test

esp2b average PM (Filterable)106920 microgram per dry standard cubic meter ( FALSE 2824 Particulate test

bag10 average PM (Filterable) 326757 microgram per dry standard cubic meter ( FALSE 2824 RATA 2005

esp1a average Sulfur Dioxide (SO2) 225 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2005

esp2b average Sulfur Dioxide (SO2) 198 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2005bag10 average Sulfur Dioxide (SO2) 26.6 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2005

esp1a average Nitrogen Oxide (NOx) 155 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2009

esp1a average Sulfur Dioxide (SO2) 190 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2009

esp1a average Nitrogen Oxide (NOx) 158 parts per million by volum e (dry) (ppmvd) FALSE

Page 72sampling_run_pollutants1

2824 RATA 2009

esp2b average Sulfur Dioxide (SO2) 190 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2009

esp2b average Nitrogen Oxide (NOx) 157 parts per million by volum e (dry) (ppmvd) FALSE 2824 RATA 2009bag10 average Sulfur Dioxide (SO2) 27 parts per million by

volum e (dry) (ppmvd) FALSE 2824 RATA 2009bag10 average Nitrogen Oxide (NOx) 154 parts per million by volum e (dry) (ppmvd @ 7% O2) FALSE 2824 2005 Mercury

Research esp1a 1 Total Mercury (Hgt) 9 microgram per normal cubic meter ( FALSE 2824 2005 Mercury

Research esp1a 2 Total Mercury (Hgt) 7.2 microgram per normal cubic meter (

FALSE 2824 2005 Mercury

Research esp1a 3 Total Mercury (Hgt) 4.5 microgram per dry

standard cubic meter ( FALSE 2824 2005 Mercury

Research esp1a 4 Total Mercury (Hgt) 3.3 microgram per dry

standard cubic meter ( FALSE 2824 2005 Mercury

Research esp1a 5 Total Mercury (Hgt) 2.5 microgram per dry

standard cubic meter ( FALSE 2824 2005 Mercury

Research esp1a 6 Total Mercury (Hgt) 7.2 microgram per dry

standard cubic meter ( FALSE

Page 73sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE inlet FALSE FALSE outlet concentration FALSE FALSE Inlet FALSE FALSE outlet FALSE FALSE inlet FALSE FALSE Outlet FALSE FALSE Baseline FALSE FALSE BASF MS FALSE FALSE Praxair Lig FALSE FALSE Prax PRB FALSE FALSE Calgon FALSE FALSE Calgon MC FALSE FALSE baseline FALSE FALSE Carbon injection FALSE FALSE baseline FALSE FALSE carbon 11.451 pound per hour (lb/hr)

FALSE 0.018 pound per million British Thermal Unit (lb/MMBtu) FALSE 6.287 pound per hour (lb/hr)

FALSE 0.009 pound per million British Thermal Unit (lb/MMBtu) FALSE 6.287 pound per hour (lb/hr)

FALSE 0.009 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE

Page 74sampling_run_pollutants1

FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE FALSE Baseline testing FALSE FALSE Baseline Initial testing FALSE FALSE 3.75 lb carbon feed rate FALSE FALSE 15 lb carbon injection FALSE FALSE 3.75 carbon with SEA FALSE FALSE Baseline Final

Page 75sampling_run_pollutants1

run_pollutant_comment

outlet concentration

Calgon MC

Carbon injection

Page 76sampling_run_pollutants1

Baseline testing Baseline Initial testing 3.75 lb carbon feed rate 15 lb carbon injection 3.75 carbon with SEA Baseline Final

Page 77sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL 2824 2005 Mercury

Research esp1a 1 Mercury (Hg) 0.05 microgram per gram (dry) (mg/g) FALSE 2824 2005 Mercury

Research esp1a 2 Mercury (Hg) 0.05 microgram per gram (dry) (mg/g) FALSE 2824 2005 Mercury

Research esp1a 3 Mercury (Hg) 0.05 microgram per gram (dry) (mg/g) FALSE 2824 2005 Mercury

Research esp1a 4 Mercury (Hg) 0.05 microgram per gram (dry) (mg/g) FALSE 2824 2005 Mercury

Research esp1a 5 Mercury (Hg) 0.05 microgram per gram (dry) (mg/g) FALSE 2824 2005 Mercury

Research esp1a 6 Mercury (Hg) 0.05 microgram per gram (dry) (mg/g) FALSE 2824 2006 RATA A

bag10 average Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 2006 RATA A

esp1a average Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 2006 RATA A

esp2b average Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 2006 RATA B

bag10 average Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 2006 RATA B

esp1a average Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 2006 RATA B

esp2b average Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 2007 Mercury

Research esp1a 1 Mercury (Hg) 0.06 microgram per gram (dry) (mg/g) FALSE 2824 2007 Mercury

Research esp1a 2 Mercury (Hg) 0.06 microgram per gram (dry) (mg/g) FALSE 2824 2007 Mercury

Research esp1a 3 Mercury (Hg) 0.06 microgram per gram (dry) (mg/g) FALSE 2824 2007 Mercury

Research esp1a 4 Mercury (Hg) 0.06 microgram per gram (dry) (mg/g) FALSE 2824 2007 Mercury

Research esp1a 5 Mercury (Hg) 0.06 microgram per gram (dry) (mg/g) FALSE 2824 2007 Mercury

Research esp1a 6 Mercury (Hg) 0.06 microgram per gram (dry) (mg/g) FALSE 2824 2009 Mercury

and Trace Metals bag10 1 Mercury (Hg) 0.033 parts per million (dry) (ppm) FALSE 2824 2009 Mercury

and Trace Metals bag10 2 Mercury (Hg) 0.033 parts per million (dry) (ppm) FALSE 2824 2009 Mercury

and Trace Metals esp1a 1 Mercury (Hg) 0.056 parts per million (dry) (ppm) FALSE 2824 2009 Mercury

and Trace Metals esp1a 2 Mercury (Hg) 0.056 parts per million (dry) (ppm) FALSE 2824 MerCap testing

ba10 1 Mercury (Hg) 0.05 microgram per gram (dry) (mg/g) FALSE 2824 MerCap testing

ba10 2 Mercury (Hg) 0.05 microgram per gram (dry) (mg/g) FALSE 2824 MerCap testing

ba10 3 Mercury (Hg) 0.05 microgram per gram (dry) (mg/g) FALSE 2824 MerCap testing

ba10 4 Mercury (Hg) 0.05 microgram per gram (dry) (mg/g) FALSE 2824 MerCap testing

ba10 5 Mercury (Hg) 0.05 microgram per gram (dry) (mg/g) FALSE 2824 MerCap testing

ba10 6 Mercury (Hg) 0.05 microgram per gram (dry) (mg/g) FALSE 2824 Particulate test

bag10 average Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 Particulate test

esp1a average Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 Particulate test

esp2b average Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 RATA 2005bag10 average Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 RATA 2005

esp1a average Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 RATA 2005

esp2b average Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 RATA 2007bag10 average Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 RATA 2007

esp1a average Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 RATA 2007

esp2b average Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 RATA 2008bag10 average Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 RATA 2008

esp1a average Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 RATA 2008

esp2b average Mercury (Hg) 0.05 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 RATA 2009bag10 average Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 RATA 2009

esp1a average Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE 2824 RATA 2009

esp2b average Mercury (Hg) 0.06 mi lligramper kilogram (dry) (mg/kg) FALSE

Page 78sampling_run_fuel

fuel_conc_MDL

Page 79