San Joaquin Valley Air Pollution Control District 

Compliance Source Test Report 

Panoche Energy Center 

Panoche Facility 

Turbine 1 

Prepared by 

Aeros Environmental, Inc. 

Determination of Concentrations and Emissions of 

Particulate, NOx, CO, VOC, NH3, Fuel Sulfur (SOx as 502) and Relative 

Accuracy Test Audit (RATA) 

Project 280-6747A 

Tested May 11, 2010 
AEROS ENVIRONMENTAL, INC. 

Panoche Energy Center 

Panoche Facility 

Turbine 1 

Pollutant ppm 

2.63 

NO. 2.57 

2.60 

Mean 2.60 

2.62 

CO 2.02 

3.88 

Mean 2.84 

2. 10 

NH, 2. 11 

2.17 

Mean 2.13 

0.0 

VOC 0.0 

0.0 

Mean <0.15 

gr/DSCF 

0.00086 

Particulate 0.00065 

0.00052 

Mean 0.00068 

gr/100DSCF 

AsSin 

Summary Of Results 

ppm@ 

%~ Ib/hr Ib/MMBtu 

1.96 6.50 0.0071 

1.91 6.35 0.0069 

1.94 6.44 0.0071 

1.94 6.43 0.0071 

1.95 3.94 0.0043 

1.50 3.04 0.0033 

2.90 5.85 0.0064 

2.12 4.28 0.0047 

1.56 1.92 

1.58 1.93 

1.62 1.98 

1.58 1.94 

0.0 0.00 0.0000 

0.0 0.00 0.0000 

0.0 0.00 0.0000 

<0.11 <0.1 3 <0.0001 

gT/SeF Ib/hr Ib/MMBtu 

0.00076 2.769 0.00279 

0.00058 2.184 0.00213 

0.00046 1.767 0.00169 

0.00060 2.240 0.00220 

Ib/hr Ib/MMBtu 

As SO~ in As SOl in 

Project 280·6747 A 

May 11, 201 0 

Permit No. C·7220·1·0 

Permit 

Limits 

2.5 ppm@1 5% 0 2 

and 

8.03 Ib/hr 

6.0 ppm@15% 0 2 

and 

11.81 Ib/hr 

10 ppm @ 15% Oz 

and 

11.90 Ib/hr 

2.0 ppm@ 15% 0 2 

and 

2.671b/hr 

0.1 gr/DSCF 

and 

6.00 Ib/hr 

1 9r/100 DSCF 

Fuel Sulfur Fuel Gas Stack Exhaust StaCk Exhaust and 

<0.06 <0.149 <0.0002 2.51 Ib/hr 

Comments 

vae Reported Results Based on Detection Limit of Prooane 

2009 Historical HAPS to vae Ratio- O.777 

Calculated HAPS=O.10 Ib/hr 
Panoche Energy Center 

Panache Facility 

Turbine 1 

Instrument Aeros 

°2% 12.95 

NOx@15% 1.95 

CO 15% 2.85 

Instrument Aeros 

° 2% 12.95 

NOx Ib/MMBtu 0.0071 

Client 

13.00 

1.98 

2.46 

Client 

13.00 

0.0072 

AEROS ENVIRONMENTAL, INC. 

Summary Of Results 

RATA Results Part 60 

RM AS Difference Oifference+CC 

0.45 N/A 0.05 N/A 

2.43 1.90 0.03 N/A 

16.17 7.67 0.39 0.46 

RATA Results Part 75 

RM Difference Bias Adjustment 

0.45 0.05 N/A 

2.25 0.00009 1.00 

Project 280-6747A 

May II, 2010 

Permit No. C-7220-1-0 

limits 

1 % Difference 

20% RM or 10% AS 

10% RM or 5% AS or 

Difference+CC<5ppm 

Annual Limits 

7.5% RM or 0.7% Difference 

7.5"1. RM or 

O.015Ib/MMBtu Difference 
San Joaquin Valley Air Pollution Control District 

Compliance Source Test Report 

Panoche Energy Center 

Panoche Facility 

Turbine 2 

Prepared by 

Aeros Environmental, Inc. 

Determination of Concentrations and Emissions of 

Particulate, NOx, CO, VOC, NH3, Fuel Sulfur (SOx as 502) and Relative 

Accuracy Test Audit (RATA) 

Project 280-6747B 

Tested May 12, 2010 
AEROS ENVIRONMENTAL, INC. 

Panoche Energy Center 

Panoche Facility 

Turbine 2 

Pollutant ppm 

2.82 

NOx 2.87 

2.89 

Mean 2.86 

2.12 

CO 2.06 

1.97 

Mean 2.05 

1.81 

NH, 1.89 

1.84 

Mean 1.85 

0.0 

VOC 0.0 

0.0 

Mean <0.15 

gr/DSCF 

0.00043 

Particulate 0.00033 

0.00047 

Mean 0.00041 

gr/100DSCF 

AsSln 

Summary Of Results 

ppm@ 

15°/c. O2 Ib/hr IblMMBtu 

2.11 7.01 0.0077 

2.14 7.14 0.0078 

2.15 7.19 0.0078 

2.13 7.11 0.0078 

1.59 3.21 0.0035 

1.54 3.12 0.0034 

1.47 2.99 0.0033 

1.53 3.11 0.0034 

1.35 1.66 

1.41 1.74 

1.37 1.69 

1.37 1.70 

0.0 0.00 0.0000 

0.0 0.00 0.0000 

0.0 0.00 0.0000 

<0.11 <0.13 <0.0001 

grlSCF Ib/hr Ib/MMBtu 

0.00039 1.430 0.00141 

0.00030 1.104 0.00107 

0.00042 1.591 0.00155 

0.00037 1.375 0.00134 

Ib/hr Ib/MMBtu 

As 502 in As S02 in 

Project 280·67478 

May 12, 2010 

Permit No. C·7220·2·0 

Permit 

Limits 

2.5 ppm@15%02 

and 

8.031b/hr 

6.0 ppm @ 15% O2 

and 

11.811b/hr 

10 ppm@15%02 

and 

11.901b/hr 

2.0 ppm@15%02 

and 

2.671b/hr 

0.1 gr/DSCF 

and 

6.00 Ib/hr 

1 gr/100 DSCF 

Fuel Sulfur Fuel Gas Stack Ex.haust Stack Exhaust and 

<0.06 <0.150 <0.0002 2.51 lb/hr 

Comments 

voe Reported Results Based on Detection limit of Propane 

2009 Historical HAPS to voe Ratio-D.777 

Calculated HAPS- O.10 Ib/hr 
Panache Energy Center 

Panache Facility 

Turbine 2 

Instrument Aeros 

°2 % 12.94 

NOx (Ql15% 2.12 

CO@1S% 1.99 

Instrument Aeros 

°2% 12.94 

~.9x Ib/MMBtu 0.0077 __ 

Client 

12.96 

2.14 

1.96 

Client 

12.96 

0.0078 

AEROS ENVIRONMENTAL, INC. 

Summary Of Results 

RATA Results Part 60 

RM AS Difference Oifference+CC 

0.21 N/A 0.02 N/A 

3.56 3.02 0.02 N/A 

3.73 1.24 0.03 0.07 

RATA Results Part 75 

RM Difference Bias Adjustment 

0.21 0.02 N/A 

3.59 0.00010 1.00 

Project 280-67478 

May 12, 2010 

Permit No. C-7220-2-0 

limits 

1% Difference 

20% RM or 10% AS 

10% RM or 5% AS or 

Difference+CC<5ppm 

Annual Limits 

7.5% RM or 0.7% Difference 

7.5% RM or 

O.015Ib/MMBtu Difference - - - ---- --
San Joaquin Valley Air Pollution Control District 

Compliance Source Test Report 

Panoche Energy Center 

Panoche Facility 

Turbine 3 

Prepared by 

Aeros Environmental, Inc. 

Determination of Concentrations and Emissions of 

Particulate, NOx, CO, VOC, NH3, Fuel Sulfur (Sox as 502) and Relative 

Accuracy Test Audit (RATA) 

Project 280-6747C 

Tested May 18, 2010 
AEROS ENVIRONMENTAL, INC. 

Panoche Energy Center 

Panoche Facility 

Turbine 3 

Pollutant ppm 

2.87 

NOx 2.85 

2.85 

Mean 2.86 

0.73 

CO 0.92 

0.87 

Mean 0.84 

1.81 

NH, 1.99 

2.04 

Mean 1.95 

0.0 

VOC 0.0 

0.0 

Mean <0.15 

gr/DSCF 

0.00051 

Particulate 0.00054 

0.00046 

Mean 0.00051 

gr/100DSCF 

AsS In 

Summary Of Results 

ppm@ 

15% 0 2 Ib/hr Ib/MMBtu 

2.12 7.06 0.0077 

211 7.02 0.0077 

2.10 6.99 0.0076 

2.11 7.02 0.0077 

0.54 1.09 0.0012 

0.68 1.37 0.0015 

0.64 1.30 0.0014 

0.62 1.25 0.001 4 

1.34 1.65 

1.46 1.80 

1.51 1.86 

1.44 1.77 

0.0 0.00 0.0000 

0.0 0.00 0.0000 

0.0 0.00 0.0000 

<0.11 <0.13 <0.0001 

grlSCF Ib/hr Ib/MMBtu 

0.00046 1.747 0.00168 

0.00048 1.845 0.00176 

0.00041 1.580 0.00149 

0.00045 1.724 0.00164 

Ib/hr Ib/MMBtu 

As S021n As S02 in 

Project 280-6747C 

May 18, 2010 

Permit No. C-7220-3'() 

Permit 

Limits 

2.5 ppm @ 15% O2 

and 

8.031b1hr 

6.0 ppm@15% Oa 

and 

11.81 Ib/hr 

10 ppm@15%02 

and 

11.901b/hr 

2.0 ppm@15% 0 2 

and 

2.67 Ib/hr 

0.1 gr/DSCF 

and 

8.00 Ib/hr 

1 gr/100 DSCF 

Fuel Sulfur Fuel Gas Stack Exhaust Stack Exhaust and 

<0.06 <0.150 <0.0002 2.51 Iblhr 

Comments 

voe Reoorted Results Based on Detection Limit of Prooane 

2009 Historical HAPS to vee Ratio 0.777 

Calculated HAPS=O.10 Iblhr 
l 

, 

Panache Energy Center 

Panache Facility 

Turbine 3 

Instrument Aeros 

0:% 12.91 

NOx@15% 2.09 

CO 15% 0.63 

Instrument Aeros 

°2% 12.91 

NOx Ib/MMBtu 0.0076 

Client 

12.93 

2.02 

0.41 

Client 

12.93 

0.0074 

AEROS ENVIRONMENTAL, INC. 

Summary Of Results 

RATA Results Part 60 

RM AS Difference Difference+CC 

0.27 NfA 0.02 NfA 

3.96 3.31 0.07 NfA 

37.37 3.94 0.22 0.24 

RATA Results Part 75 

RM Difference Bias Ad ustment 

0.27 0.02 NfA 

4.09 0.00026 1.04 

Project 280-6747C 

May 18, 2010 

Permit No. C-7220-3'() 

limits 

1% Difference 

20% RM or 10% AS 

10% RM or 5% AS or 

Difference+CC<5ppm 

Annual Limits 

7.5% RM or 0.7'1. Difference 

7.5% RM or 

0.015 IblMMBlu Difference -- - -- - --------
San Joaquin Valley Air Pollution Control District 

Compliance Source Test Report 

Panoche Energy Center 

Panoche Facility 

Turbine 4 

Prepared by 

Aeros Environmental, Inc. 

Determination of Concentrations and Emissions of 

Particulate, NOx, CO, VOC, NH3, Fuel Sulfur (Sox as 502) and Relative 

Accuracy Test Audit (RATA) 

Project 280·67470 

Tested May 19, 2010 
AEROS ENVIRONMENTAL, INC. 

Panache Energy Center 

Panache Facility 

Turbine 4 

Pollutant ppm 

2.84 

NOx 2.84 

2.79 

Mean 2.82 

2.25 

CO 1.38 

1.53 

Mean 1.72 

1.78 

NH, 1.89 

1.80 

Mean 1.82 

0.0 

VOC 0.0 

0.0 

Mean <0.15 

grJDSCF 

0.00076 

Particulate 0.00061 

0.00095 

Mean 0.00077 

gr/100DSCF 

AsS in 

Summary Of Results 

ppm@ 

15% O2 Ib/hr Ib/MMBtu 

2.11 6.95 0.0077 

2.11 6.91 0.0077 

2.08 6.77 0.0076 

2.10 6.88 0.0077 

1.67 3.34 0.0037 

1.03 2.04 0.0023 

1.14 2.26 0.0025 

1.28 2.55 0.0028 

1.32 1.60 

1.41 1.70 

1.34 1.61 

1.36 1.63 

0.0 0.00 0.0000 

0.0 0.00 0.0000 

0.0 0.00 0.0000 

<0.11 <0.13 <0.0001 

grlSCF Ib/hr Ib/MMBtu 

0.00068 2.529 0.00249 

0.00054 2.021 0.001 98 

0.00085 3.128 0.00310 

0.00069 2.559 0.00252 

Ib/hr IbfMMBtu 

AsS02 in As 502 in 

Project 280-67470 

May 19, 2010 

Permit No. C-7220-4-0 

Permit 

Limits 

2,5 ppm@15%02 

and 

8.031b/hr 

6.0 ppm@15%02 

and 

11.811bfhr 

10 ppm @ 15% O2 

and 

11.901b/hr 

2.0 ppm @ 15% O2 

and 

2.671b/hr 

0.1 g rlDSCF 

and 

6.001blhr 

1 gr/100 DSCF 

Fuel Sulfur Fuel Gas Stack Exhaust Stack Exhaust and 

<0.06 <0.148 <0.0002 2.51 Ib/hr 

Comments 

vae Reported Results Based on Detection Limit of Propane 

2009 Historical HAPS to vae Ratio- C.77? 

Calculated HAPS-O.10 Ib/hr 
, 

Panoche Energy Center 

Panoche Facility 

Turbine 4 

Instrument Aeros 

°2% 12.98 

NOx@15% 2.09 

CO@15% 1.27 

Instrument Aeros 

°2% 12.98 

NOx Ib/MMBtu 0.0076 

Client 

12.99 

2.12 

1.24 

Client 

12.99 

0.0077 

AEROS ENVIRONMENTAL, INC. 

Summary Of Results 

RATA Results Part 60 

RM AS Difference Difference+CC 

0.11 N/A 0.00 N/A 

2.25 1.89 0.03 N/A 

6.31 1.33 0.03 0.08 

RATA Results Part 75 

RM Difference Bias Ad' ustment 

0.11 0.00 N/A 

1.69 0.00008 1.00 

Project 280-67470 

May 19, 2010 

Permit No. C-7220-4-0 

Limits 

1% Difference 

20% RM or 10% AS 

10% RM or 5% AS or 

Difference+CC<5ppm 

Annual Limits 

7.5% RM or 0.7% Difference 

7.5% RM or 

0.015 Ib/MMBtu Difference