Federal Register / Vol. 71, No. 218 / Monday, November 13, 2006 / Notices 66201 

cancellations, please visit the NSF Web 

site: http://www.nsf.gov. This 

information may also be requested by 

telephoning, 703/292–8182. 

Dated: November 7, 2006. 

Susanne Bolton, 

Committee Management Officer. 

[FR Doc. 06–9182 Filed 11–9–06; 8:45 am] 

BILLING CODE 7555–01–M 

NATIONAL SCIENCE FOUNDATION 

Advisory Committee for International 

Science and Engineering; Notice of 

Meeting 

In accordance with Federal Advisory 

Committee Act (Pub. L. 92–463, as 

amended), the National Science 

Foundation announces the following 

meeting: 

Name: Advisory Committee for 

International Science and Engineering 

(25104). 

Date/Time: December 4, 2006; 8:30 a.m. to 

5 p.m. 

Place: National Science Foundation, 4201 

Wilson Boulevard, Room 1235, Arlington, 

VA. 

Type of Meeting: Open. 

Contact Person: Eduardo Feller, National 

Science Foundation, 4201 Wilson Boulevard, 

(suite 935), Arlington, VA 22230 (703) 292–

8100. 

If you are attending the meeting and need 

access to the NSF, please contact the 

individual listed above so your name may be 

added to the building access list. 

Purpose of Meeting: To provide advice on 

the programs of the Office of International 

Science and Engineering. 

Agenda: Presentation of new Committee 

Members. 

Update on work of the Office. 

Briefings on Current International 

Initiatives. 

Discussion of International Program 

Initiatives. 

Dated: November 7, 2006. 

Susanne Bolton, 

Committee Management Officer. 

[FR Doc. 06–9181 Filed 11–9–06; 8:45 am] 

BILLING CODE 7555–01–M 

NUCLEAR REGULATORY 

COMMISSION 

[Docket Nos. 50–373 and 50–374] 

Exelon Generation Company, LLC; 

Notice of Denial of Amendment to 

Facility Operating License and 

Opportunity for Hearing 

The U.S. Nuclear Regulatory 

Commission (NRC or the Commission) 

has denied a request by Exelon 

Generation Company, LLC (the licensee) 

for an amendment to Facility Operating 

Licenses NPF–11 and NPF–12, issued to 

the licensee for operation of the Lasalle 

County Station, Unit Nos. 1 and 2, 

located in LaSalle County, Illinois. 

Notice of Consideration of Issuance of 

this amendment was published in the 

Federal Register on March 28, 2006 (71 

FR 15483). 

The purpose of the licensee’s 

amendment request was to revise the 

technical specifications (TS) to change 

Surveillance Requirement (SR) 3.7.3.1 

which verifies the cooling water 

temperature supplied to the plant from 

the core standby cooling system (CSCS) 

pond (i.e., ultimate heat sink (UHS)) is 

≤ 100 °F. Currently, if the temperature 

of the cooling water supplied to the 

plant from the CSCS pond is > 100 °F, 

the UHS must be declared inoperable in 

accordance with TS 3.7.3. The license 

amendment request proposed to 

increase the temperature limit of the 

cooling water supplied to the plant from 

the CSCS pond to ≤ 101.5 °F by 

reducing the temperature measurement 

uncertainty by replacing the existing 

thermocouples with higher precision 

temperature measuring equipment. 

Should the UHS indicated temperature 

exceed 101.5 °F, Required Action B.1 

would be entered and both units would 

be placed in Mode 3 within 12 hours 

and Mode 4 within 36 hours. 

The NRC staff has concluded that the 

licensee’s request cannot be granted. 

The licensee was notified of the 

Commission’s denial of the proposed 

change by telephone on November 2, 

2006. 

By 30 days from the date of 

publication of this notice in the Federal 

Register, the licensee may demand a 

hearing with respect to the denial 

described above. Any person whose 

interest may be affected by this 

proceeding may file a written petition 

for leave to intervene pursuant to the 

requirements of 10 CFR 2.309. 

A request for a hearing or a petition 

for leave to intervene must be filed by: 

(1) First class mail addressed to the 

Office of the Secretary of the 

Commission, U.S. Nuclear Regulatory 

Commission, Washington, DC 20555–

0001, Attention: Rulemaking and 

Adjudications Staff; (2) courier, express 

mail, and expedited delivery services: 

Office of the Secretary, Sixteenth Floor, 

One White Flint North, 11555 Rockville 

Pike, Rockville, MD 20852, Attention: 

Rulemaking and Adjudications Staff; (3) 

E-mail addressed to the Office of the 

Secretary, U.S. Nuclear Regulatory 

Commission, 

HEARINGDOCKET@NRC.GOV; or (4) 

facsimile transmission addressed to the 

Office of the Secretary, U.S. Nuclear 

Regulatory Commission, Washington, 

DC 20555–0001, Attention: Rulemakings 

and Adjudications Staff at (301) 415–

1101, verification number is (301) 415–

1966. A copy of the request for hearing 

and petition for leave to intervene 

should also be sent to the Office of the 

General Counsel, U.S. Nuclear 

Regulatory Commission, Washington, 

DC 20555–0001, and it is requested that 

copies be transmitted either by means of 

facsimile transmission to (301) 415–

3725 or by e-mail to 

OGCMailCenter@nrc.gov . A copy of the 

request for hearing and petition for 

leave to intervene should also be sent to 

Mr. Bradley J. Fewell, Assistant General 

Counsel, Exelon Generation Company, 

LLC, 200 Exelon Way, Kennett Square, 

PA 19348, attorney for the licensee. For 

further details with respect to this 

action, see (1) the application for 

amendment dated March 13, 2006, as 

supplemented by letters dated July 13 

and August 4, 2006, and (2) the 

Commission’s letter to the licensee 

dated November 3, 2006. 

Documents may be examined, and/or 

copied for a fee, at the NRC’s Public 

Document Room (PDR), located at One 

White Flint North, Public File Area O1 

F21, 11555 Rockville Pike (first floor), 

Rockville, Maryland, and will be 

accessible electronically through the 

Agencywide Documents Access and 

Management System’s (ADAMS) Public 

Electronic Reading Room link at the 

NRC Web site http://www.nrc.gov/ 

reading-rm/adams.html. Persons who 

do not have access to ADAMS or who 

encounter problems in accessing 

documents located in ADAMS should 

contact the NRC PDR Reference staff by 

telephone at 1–800–397–4209, (301) 

415–4737, or by e-mail to pdr@nrc.gov. 

Dated at Rockville, Maryland, this 3rd day 

of November 2006. 

For the Nuclear Regulatory Commission. 

Catherine Haney, 

Director, Division of Operating Reactor 

Licensing, Office of Nuclear Reactor 

Regulation. 

[FR Doc. E6–19097 Filed 11–9–06; 8:45 am] 

BILLING CODE 7590–01–P 

NUCLEAR REGULATORY 

COMMISSION 

[Docket No. 030–29319; License No. 42–

26838–01; EA–06–021] 

In the Matter of H&G Inspection 

Company, Inc., Houston, TX; 

Confirmatory Order (Effective 

Immediately) 

I 

H&G Inspection Company, Inc. (H&G), 

is the holder of Materials License No. 


cprice-sewell on PROD1PC66 with NOTICES