Monroe Power Plant Unit 3 

Emissions Test Summary Report 

Prepared for: 

DTE Energy Monroe Power Plant 

Monroe, Michigan 

DTE Monroe Power Plant 

3500 East Front Street 

Monroe, Michigan 48162 

Project No. 10-3991.01 

August 31, 2010 

BT Environmental Consulting, Inc. 

2615 Wolcott Street 

Ferndale, Michigan 48220 

(248) 548-8070 
Executive Summary

BT Environmental Consulting, Inc. (BTEC) was retained by DTE Energy (DTE) to evaluate air 

pollutant emissions rates from Monroe Power Plant Unit 3 (MONPP Unit 3) located in Monroe, 

Michigan. The test project consisted of (1) measurement of exhaust gas flowrates and moisture 

content, (2) measurement of exhaust gas oxygen (O2) and carbon dioxide (CO2) concentrations, 

(3) measurement of exhaust gas dioxin and furan concentrations and emission rates, and (4) 

measurement of fuel sample higher heating value. Testing for this project was completed during 

the period beginning June 29 and ending July 1, 2010. The emissions test program was requested 

in a letter sent to DTE by the United States Environmental Protection Agency (U.S. EPA) 

pursuant to U.S. EPA authority under Section 114 of the Clean Air Act. 

Testing of Unit 3 consisted of triplicate 480-minute test runs for each parameter. Sampling was 

performed utilizing United States Environmental Protection Agency (USEPA) methods. The 

results of the testing are summarized in Table 1. Detailed results for each run are appended as 

Tables 2-4. 

Table 1 

Overall Emission Summary 

Pollutant Emission Rate lb/MMBtu Emission Rate ng/dscm @7% O2

Dioxins 4.7E-11 0.051 

Furans 5.6E-11 0.061 

PCBs 4.9E-10 0.53 

1: See Table 3 for individual D/F/PCB emissions lb/MMBtu 

2: See Table 4 for individual D/F/PCB emissions in ng/dscm @ 7% O2 

DTE Monroe Power Plant BTEC Project No. 10-3991.01 

Unit 3 Emissions Test Report 8/31/2010 

i
DTE Monroe Power Plant BTEC Project No. 10-3991.01 

Unit 3 Emissions Test Report 8/31/2010 

ii

TABLE OF CONTENTS

1.0 INTRODUCTION............................................................................................................... 1

2.0 PROCESS DESCRIPTION ............................................................................................... 1

3.0 SAMPLING AND ANALYTICAL METHODOLOGIES.............................................. 1

3.1 EXHAUST GAS VELOCITY AND MOISTURE CONTENT ......................................................... 2 

3.2 OXYGEN AND CARBON DIOXIDE (USEPA METHOD 3A).................................................... 2 

3.3 DIOXIN/FURAN HAPS (USEPA METHOD 23)..................................................................... 3 

4.0 TEST RESULTS ................................................................................................................. 3

TABLES

Table 1 – Overall Emissions Summary 

Table 2 – Unit 3 Dioxin/Furan HAPs Laboratory Results 

Table 3 – Unit 3 Dioxin/Furan HAPs Emission Rates (lb/mmbtu) 

Table 4 – Unit 3 Dioxin/Furan HAPs Emission Rates (ng/dscm @ 7%O2) 

FIGURES

Figure 1 – Boiler 3 Exhaust Stack Traverse Point Diagram 

Figure 2 – USEPA Method 3A Sampling Train Diagram 

Figure 3 – USEPA Method 23 Sampling Train Diagram 

APPENDICES

Appendix A – Field and Computer Generated Raw Data and Field Notes 

Appendix B – Calibration Data 

Appendix C – Raw CEM Data 

Appendix D – Laboratory Analytical Results 

Appendix E – Example Calculations 

Appendix F – Production Data 
1.0 Introduction

BT Environmental Consulting, Inc. (BTEC) was retained by DTE Energy (DTE) to evaluate air 

pollutant emissions rates from Monroe Power Plant Unit 3 (MONPP Unit 3) located in Monroe, 

Michigan. The test project consisted of (1) measurement of exhaust gas flowrates and moisture 

content, (2) measurement of exhaust gas oxygen (O2) and carbon dioxide (CO2) concentrations, 

(3) measurement of exhaust gas dioxin and furan concentrations and emission rates, and (4) 

measurement of fuel sample higher heating value. Testing for this project was completed during 

the period beginning June 29 and ending July 1, 2010. The emissions test program was requested 

in a letter sent to DTE by the United States Environmental Protection Agency (U.S. EPA) 

pursuant to U.S. EPA authority under Section 114 of the Clean Air Act. 

The following BTEC professionals participated in conducting this study: Thom Snyder, Project 

Manager; Jon Beach, Staff Environmental Engineer; and Matthew Smith, Environmental 

Technician. Mr. Mark Grigerite with DTE provided on-site coordination for this project. 

2.0 Process Description

The Monroe Power Plant (MONPP) located at 3500 E. Front Street in Monroe, Michigan, 

employs the use of four (4) Babcock and Wilcox coal-fired boilers (Units 1-4) each designed to 

produce nominally 5,717,865 pounds per hour of steam. Units 1 and 4 have a General Electric 

turbine generator with a rated capability of 817 gross megawatts (GMW). Units 2 and 3 have 

Westinghouse turbine generators each with a rated capability of 823 GMW. Units 1 and 2 

exhaust into a common stack (Stack 1). Unit 3 and Unit 4 exhaust into individual stacks. The 

typical coal blend for Unit 3 is a 65% low-sulfur western (LSW) / 35% mid-sulfur eastern 

(MSE). Full load conditions for the Unit will be nominally 740-785 MW, but may be lower 

during the testing period due to unit-specific issues. Testing will occur on Unit 3 as close to full 

load conditions as possible, but not less than 90% of full load.

3.0 Sampling and Analytical Methodologies

Sampling and analytical methodologies for the emissions test program can be separated into 

three categories as follows: 

(1) Measurement of exhaust gas velocity, molecular weight, and moisture content; 

(2) Measurement of exhaust gas oxygen (O2) and carbon dioxide (CO2) concentrations using 

the procedures of U.S. EPA Method 3A; 

(3) Measurement of exhaust gas dioxin/furan HAP concentrations and emission rates using 

U.S. EPA Method 23. 

Descriptions of sampling and analytical methodologies by category are summarized by Sections 

3.1 through 3.3, respectively. 

DTE Monroe Power Plant BTEC Project No. 10-3991.01 

Unit 3 Emissions Test Report 8/31/2010 

 

1
3.1 Exhaust Gas Velocity and Moisture Content

Measurement of exhaust gas velocity and moisture content were conducted using the following 

reference test methods codified at Title 40, Part 60, Appendix A of the Code of Federal 

Regulations (40 CFR 60, Appendix A): 

• Method 1 -“Sample and Velocity Traverses for Stationary Sources” 

• Method 2 -“Determination of Stack Gas Velocity and Volumetric Flowrate” 

• Method 4 -“Determination of Moisture Content in Stack Gases”

Stack gas velocity traverses were conducted in accordance with the procedures outlined in 

Methods 1 and 2 (see Figure 1 for an exhaust stack traverse point diagram). An S-type pitot tube 

with a thermocouple assembly, calibrated in accordance with Method 2, Section 4.1.1, was used 

to measure exhaust gas velocity pressures (using a manometer) and temperatures during testing. 

The S-type pitot tube dimensions were within specified limits, therefore, a baseline pitot tube 

coefficient of 0.84 (dimensionless) was assigned. 

A cyclonic flow check was performed at the sampling location. The existence of cyclonic flow 

is determined by measuring the flow angle at each sample point. The flow angle is the angle 

between the direction of flow and the axis of the stack. If the average of the absolute values of 

the flow angles is greater than 20 degrees, cyclonic flow exists. The null angle was determined 

to be less than 20 degrees at each sampling point. 

Exhaust gas moisture content was evaluated using Method 4. Exhaust gas was extracted as part 

of the Method 23 sampling train (see Figure 3 for a schematic of the sampling train). Exhaust 

gas moisture content was then determined gravimetrically. 

3.2 Oxygen and Carbon Dioxide (USEPA Method 3A) 

Exhaust gas O2 and CO2 concentrations were measured using the procedures of 40 CFR 60, 

Appendix A, Method 3A, “Determination of Oxygen and Carbon Dioxide Concentrations in 

Emissions from Stationary Sources”. The O2 content of the gas stream was measured using a 

Teledyne paramagnetic O2 gas analyzer. The CO2 content of the gas stream was measured using 

a Teledyne infrared CO2 gas analyzer. The gas stream was drawn through a stainless-steel probe 

with a heated in-line filter to remove any particulate, a heated Teflon® sample line, through a 

refrigerated Teflon® sample conditioner to remove the moisture from the sample before it 

entered the analyzers. Data was recorded on a PC equipped with data acquisition software. 

Recorded concentrations were averaged and reported for the duration of each 480-minute test (as 

drift corrected per Method 7E). A drawing of the sampling train used for the testing program is 

presented as Figure 2. 

In accordance with Method 7E, a 4-point (zero, low, mid, and high) bias check and calibration 

check was performed on the analyzers prior to initiating the test program. Following each test 

run, a 2-point (zero and high) calibration drift check was performed. 

DTE Monroe Power Plant BTEC Project No. 10-3991.01 

Unit 3 Emissions Test Report 8/31/2010 

 

2
3.3 Dioxin/furan HAP (USEPA Method 23) 

40 CFR 60, Appendix A, Method 23, “Determination of Polychlorinated Dibenzo-p-dioxins 

and Polychlorinated Dibenzofurans from Municipal Waste Combustors” was used to evaluate 

dioxin/furan HAP concentrations. The Method 23 sampling train consisted of (1) a borosilicate 

glass or quartz nozzle, (2) a steel probe w/ glass liner, (3) a heated quartz fiber filter assembly, 

(4) a glass recirculating ice water condenser system, (5) a XAD-2 sorbent trap, (6) an empty pot 

bellied impinger, (7) a set of five GS impingers, (8) a length of sample line, and (9) a Nutech®

control case equipped with a pump, dry gas meter, and calibrated orifice. Prior to each test, the 

second and third impingers were filled with 100 ml of HPLC water, the first and fourth 

impingers were empty, and the fifth impinger contained approximately 300 g of silica gel 

desiccant. A schematic drawing of the D/F sample train is provided as Figure 3. 

After completion of the final leak test for each test run, the impinger train was carefully 

disassembled. The liquid volume of each impinger was measured gravimetrically and any mass 

increase was noted on field sheets. The adsorbent module was removed from the sampling train, 

tightly capped at both ends, labeled, covered with aluminum foil, and stored in an iced cooler for 

later transport to the laboratory. The filter was recovered and placed in its original Petri dish. 

The nozzle, probe, filter housing, and condenser were brushed and triple rinsed with acetone and 

then methylene chloride (MeCl2) which was collected in a pre-cleaned sample container. The 

nozzle, probe, filter housing, and condenser were then triple rinsed with toluene which was 

collected in a separate sample container. 

BTEC labeled each container with the test number, test location, and test date, and marked the 

level of liquid on the outside of the container. In addition, blank samples of the HPLC water, 

acetone, MeCl2, toluene, adsorbent module, and filter were collected. Samples were couriered by 

Maxxam Analytics, Ltd. (Maxxam) personnel to the Maxxam laboratory for analysis. 

4.0 Test Results

Table 1 

Overall Emission Summary 

Pollutant Emission Rate lb/MMBtu Emission Rate ng/dscm @7% O2

Dioxins 4.7E-11 0.051 

Furans 5.6E-11 0.061 

PCBs 4.9E-10 0.53 

1: See Table 3 for individual D/F/PCB emissions lb/MMBtu 

2: See Table 4 for individual D/F/PCB emissions in ng/dscm @ 7% O2 

Detailed results for each run are appended as Tables 2-4. Field and computer generated data for 

each test run are available in Appendix A, as well as all other applicable field data. Equipment 

calibration and span gas documentation is presented in Appendix B. Raw CEMs data is 

presented in Appendix C. Laboratory analysis is available in Appendix D. Example calculations 

are available in Appendix E. Production data is available in Appendix F. 

DTE Monroe Power Plant BTEC Project No. 10-3991.01 

Unit 3 Emissions Test Report 8/31/2010 

 

3
DTE Monroe Power Plant BTEC Project No. 10-3991.01 

Unit 3 Emissions Test Report 8/31/2010 

 

4

Limitations

The information and opinions rendered in this report are exclusively for use by DTE Energy. 

BTEC will not distribute or publish this report without DTE Energy’s consent except as required 

by law or court order. BTEC accepts responsibility for the competent performance of its duties 

in executing the assignment and preparing reports in accordance with the normal standards of the 

profession, but disclaims any responsibility for consequential damages. 

This report was prepared by: 

Brandon V. Chase 

Staff Environmental Engineer 

This report was reviewed by: 

Barry P. Boulianne 

Senior Project Manager 
Tables 
Table 2

Unit 3 Dioxins and Furans Laboratory Results Summary

DTE Energy Monroe Power Plant

Monroe, Michigan

BTEC Project No. 10-3991.01

Sampling Date: June 29-July 1, 2009

 

Parameter Run 1 Run 2 Run 3 Average

Test Run Date 6/29/2010 6/30/2010 7/1/2010

Test Run Time 7:52-16:40 8:40-17:59 7:52-16:40

Exhaust Gas Flowrate (dscfm) 1,764,605 1,738,348 1,762,849 1,755,267

Sample Volume, Vmstd (dscf) 313.1 309.9 311.8 311.6

O2 Concentration (%, Corrected as per Method 7E) 6.1 6.2 6.2 6.1

CO2 Concentration (%, Corrected as per Method 7E) 13.9 13.5 13.5 13.6

Moisture % 13.6 13.7 7.0 11.5

Fd 9,738 9,738 9,738 9,738

Laboratory Result (pg)

2,3,7,8-TCDD 30 30 30 30

1,2,3,7,8-PeCDD 30 30 30 30

1,2,3,4,7,8-HxCDD 30 30 30 30

1,2,3,6,7,8-HxCDD 30 30 30 30

1,2,3,7,8,9-HxCDD 30 30 30 30

1,2,3,4,6,7,8-HpCDD 30 30 30 30

OCDD 300 300 300 300

2,3,7,8-TCDF 30 30 30 30

1,2,3,7,8-PeCDF 30 30 30 30

2,3,4,7,8-PeCDF 30 30 30 30

1,2,3,4,7,8-HxCDF 30 30 30 30

1,2,3,6,7,8-HxCDF 30 30 30 30

2,3,4,6,7,8-HxCDF 30 30 30 30

1,2,3,7,8,9-HxCDF 30 30 30 30

1,2,3,4,6,7,8-HpCDF 30 30 30 30

1,2,3,4,7,8,9-HpCDF 30 30 30 30

OCDF 300 300 300 300

3,3',4,4'-TCB (PCB77)* 300 300 300 300

3,4,4',5-TCB (PCB81)* 300 300 300 300

2,3,3',4,4'-PeCB (PCB105)* 300 300 300 300

2,3,4,4',5-PeCB (PCB114)* 300 300 300 300

2,3',4,4',5-PeCB (PCB118)* 680 720 540 647

2',3,4,4',5-PeCB (PCB123)* 300 300 300 300

3,3',4,4',5-PeCB (PCB126)* 600 600 600 600

2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PCBs156/157)* 300 300 300 300

2,3',4,4',5,5'-HxCB (PCB167)* 300 300 300 300

3,3',4,4',5,5'-HxCB (PCB169)* 300 300 300 300

2,3,3',4,4',5,5'-HpCB (PCB189)* 300 300 300 300

dscfm = dry standard cubic feet per minute

dscf = dry standard cubic feet

ng/dscm @ 7%O2 = nanograms per dry standard cubic meter corrected to 7% Oxygen

lb/mmbtu = pounds per million btu

31.31 = Ft^3 per m^3

453.6 = grams per pound

* PCB results from Maxxam are in ng. Results displayed here converted to pg.

All results were below rdl (reportable detection limit) except PCB118 (bolded). RDL used for calculations in all other cases.

equations:

lb/mmbtu = concentration(pg)/(10^12) *Fd/Vmstd * 1/453.6 * 20.9/(20.9-O2)

ng/dscm @ 7%O2 = concentration(pg) * (1/1000) * (35.31/Vmstd) * (20.9-7)/(20.9-O2)
Table 3

Unit 3 Dioxins and Furans Emission Test Results Summary (lb/mmbtu)

DTE Energy Monroe Power Plant

Monroe, Michigan

BTEC Project No. 10-3991.01

Sampling Date: June 29-July 1, 2009

 

Parameter Run 1 Run 2 Run 3 Average

Test Run Date 6/29/2010 6/30/2010 7/1/2010

Test Run Time 7:52-16:40 8:40-17:59 7:52-16:40

Exhaust Gas Flowrate (dscfm) 1,764,605 1,738,348 1,762,849 1,755,267

Sample Volume, Vmstd (dscf) 313.1 309.9 311.8 311.6

O2 Concentration (%, Corrected as per Method 7E) 6.1 6.2 6.2 6.1

CO2 Concentration (%, Corrected as per Method 7E) 13.9 13.5 13.5 13.6

Moisture % 13.6 13.7 7.0 11.5

Fd 9,738 9,738 9,738 9,738

Emissions (lb/MMBtu)

DIOXINS

2,3,7,8-TCDD 2.9E-12 2.9E-12 2.9E-12 2.9E-12

1,2,3,7,8-PeCDD 2.9E-12 2.9E-12 2.9E-12 2.9E-12

1,2,3,4,7,8-HxCDD 2.9E-12 2.9E-12 2.9E-12 2.9E-12

1,2,3,6,7,8-HxCDD 2.9E-12 2.9E-12 2.9E-12 2.9E-12

1,2,3,7,8,9-HxCDD 2.9E-12 2.9E-12 2.9E-12 2.9E-12

1,2,3,4,6,7,8-HpCDD 2.9E-12 2.9E-12 2.9E-12 2.9E-12

OCDD 2.9E-11 2.9E-11 2.9E-11 2.9E-11

Dioxins Totals: 4.6E-11 4.7E-11 4.7E-11 4.7E-11

FURANS

2,3,7,8-TCDF 2.9E-12 2.9E-12 2.9E-12 2.9E-12

1,2,3,7,8-PeCDF 2.9E-12 2.9E-12 2.9E-12 2.9E-12

2,3,4,7,8-PeCDF 2.9E-12 2.9E-12 2.9E-12 2.9E-12

1,2,3,4,7,8-HxCDF 2.9E-12 2.9E-12 2.9E-12 2.9E-12

1,2,3,6,7,8-HxCDF 2.9E-12 2.9E-12 2.9E-12 2.9E-12

2,3,4,6,7,8-HxCDF 2.9E-12 2.9E-12 2.9E-12 2.9E-12

1,2,3,7,8,9-HxCDF 2.9E-12 2.9E-12 2.9E-12 2.9E-12

1,2,3,4,6,7,8-HpCDF 2.9E-12 2.9E-12 2.9E-12 2.9E-12

1,2,3,4,7,8,9-HpCDF 2.9E-12 2.9E-12 2.9E-12 2.9E-12

OCDF 2.9E-11 2.9E-11 2.9E-11 2.9E-11

Furans Totals: 5.5E-11 5.6E-11 5.6E-11 5.6E-11

Polychlorinated Biphenols (PCB)

3,3',4,4'-TCB (PCB77) 2.9E-11 2.9E-11 2.9E-11 2.9E-11

3,4,4',5-TCB (PCB81) 2.9E-11 2.9E-11 2.9E-11 2.9E-11

2,3,3',4,4'-PeCB (PCB105) 2.9E-11 2.9E-11 2.9E-11 2.9E-11

2,3,4,4',5-PeCB (PCB114) 2.9E-11 2.9E-11 2.9E-11 2.9E-11

2,3',4,4',5-PeCB (PCB118) 6.6E-11 7.1E-11 5.3E-11 6.3E-11

2',3,4,4',5-PeCB (PCB123) 2.9E-11 2.9E-11 2.9E-11 2.9E-11

3,3',4,4',5-PeCB (PCB126) 5.8E-11 5.9E-11 5.9E-11 5.9E-11

2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PCBs156/157) 2.9E-11 2.9E-11 2.9E-11 2.9E-11

2,3',4,4',5,5'-HxCB (PCB167) 2.9E-11 2.9E-11 2.9E-11 2.9E-11

3,3',4,4',5,5'-HxCB (PCB169) 2.9E-11 2.9E-11 2.9E-11 2.9E-11

2,3,3',4,4',5,5'-HpCB (PCB189) 2.9E-11 2.9E-11 2.9E-11 2.9E-11

PCB Totals: 3.9E-10 3.9E-10 3.7E-10 3.8E-10

Dioxins/Furans/PCB Totals: 4.9E-10 5.0E-10 4.8E-10 4.9E-10

dscfm = dry standard cubic feet per minute

dscf = dry standard cubic feet

ng/dscm @ 7%O2 = nanograms per dry standard cubic meter corrected to 7% Oxygen

lb/mmbtu = pounds per million btu

31.31 = Ft^3 per m^3

453.6 = grams per pound

* PCB results from Maxxam are in ng. Results displayed here converted to pg.

All results were below rdl (reportable detection limit) except PCB118 (bolded). RDL used for calculations in all other cases.

equations:

lb/mmbtu = concentration(pg)/(10^12) *Fd/Vmstd * 1/453.6 * 20.9/(20.9-O2)

ng/dscm @ 7%O2 = concentration(pg) * (1/1000) * (35.31/Vmstd) * (20.9-7)/(20.9-O2)
Table 4

Unit 3 Dioxins and Furans Emission Test Results Summary (ng/dscm @7% O2)

DTE Energy Monroe Power Plant

Monroe, Michigan

BTEC Project No. 10-3991.01

Sampling Date: June 29-July 1, 2009

 

Parameter Run 1 Run 2 Run 3 Average

Test Run Date 6/29/2010 6/30/2010 7/1/2010

Test Run Time 7:52-16:40 8:40-17:59 7:52-16:40

Exhaust Gas Flowrate (dscfm) 1,764,605 1,738,348 1,762,849 1,755,267

Sample Volume, Vmstd (dscf) 313.1 309.9 311.8 311.6

O2 Concentration (%, Corrected as per Method 7E) 6.1 6.2 6.2 6.1

CO2 Concentration (%, Corrected as per Method 7E) 13.9 13.5 13.5 13.6

Moisture % 13.6 13.7 7.0 11.5

Fd 9,738 9,738 9,738 9,738

Concentrations (ng/dscm @7% O2)

DIOXINS

2,3,7,8-TCDD 0.003 0.003 0.003 0.003

1,2,3,7,8-PeCDD 0.003 0.003 0.003 0.003

1,2,3,4,7,8-HxCDD 0.003 0.003 0.003 0.003

1,2,3,6,7,8-HxCDD 0.003 0.003 0.003 0.003

1,2,3,7,8,9-HxCDD 0.003 0.003 0.003 0.003

1,2,3,4,6,7,8-HpCDD 0.003 0.003 0.003 0.003

OCDD 0.032 0.032 0.032 0.032

Dioxins Totals: 0.051 0.052 0.051 0.051

FURANS

2,3,7,8-TCDF 0.003 0.003 0.003 0.003

1,2,3,7,8-PeCDF 0.003 0.003 0.003 0.003

2,3,4,7,8-PeCDF 0.003 0.003 0.003 0.003

1,2,3,4,7,8-HxCDF 0.003 0.003 0.003 0.003

1,2,3,6,7,8-HxCDF 0.003 0.003 0.003 0.003

2,3,4,6,7,8-HxCDF 0.003 0.003 0.003 0.003

1,2,3,7,8,9-HxCDF 0.003 0.003 0.003 0.003

1,2,3,4,6,7,8-HpCDF 0.003 0.003 0.003 0.003

1,2,3,4,7,8,9-HpCDF 0.003 0.003 0.003 0.003

OCDF 0.032 0.032 0.032 0.032

Furans Totals: 0.060 0.061 0.061 0.061

Polychlorinated Biphenols (PCB)

3,3',4,4'-TCB (PCB77) 0.03 0.03 0.03 0.03

3,4,4',5-TCB (PCB81) 0.03 0.03 0.03 0.03

2,3,3',4,4'-PeCB (PCB105) 0.03 0.03 0.03 0.03

2,3,4,4',5-PeCB (PCB114) 0.03 0.03 0.03 0.03

2,3',4,4',5-PeCB (PCB118) 0.07 0.08 0.06 0.07

2',3,4,4',5-PeCB (PCB123) 0.03 0.03 0.03 0.03

3,3',4,4',5-PeCB (PCB126) 0.06 0.06 0.06 0.06

2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PCBs156/157) 0.03 0.03 0.03 0.03

2,3',4,4',5,5'-HxCB (PCB167) 0.03 0.03 0.03 0.03

3,3',4,4',5,5'-HxCB (PCB169) 0.03 0.03 0.03 0.03

2,3,3',4,4',5,5'-HpCB (PCB189) 0.03 0.03 0.03 0.03

PCB Totals: 0.42 0.43 0.41 0.42

Dioxins/Furans/PCB Totals: 0.53 0.54 0.52 0.53

dscfm = dry standard cubic feet per minute

dscf = dry standard cubic feet

ng/dscm @ 7%O2 = nanograms per dry standard cubic meter corrected to 7% Oxygen

lb/mmbtu = pounds per million btu

31.31 = Ft^3 per m^3

453.6 = grams per pound

* PCB results from Maxxam are in ng. Results displayed here converted to pg.

All results were below rdl (reportable detection limit) except PCB118 (bolded). RDL used for calculations in all other cases.

equations:

lb/mmbtu = concentration(pg)/(10^12) *Fd/Vmstd * 1/453.6 * 20.9/(20.9-O2)

ng/dscm @ 7%O2 = concentration(pg) * (1/1000) * (35.31/Vmstd) * (20.9-7)/(20.9-O2)
Figures 
diameter = 336 inches

Points Distance "

1 14.78

2 49.06

3 99.46

4 236.54

5 286.94

6 321.22

Figure No. 1

Site: Sampling Date:

DTE Energy

Monroe Power Plant

Unit 3 Exhaust

BT Environmental Consulting, 

Inc.

2615 Wolcott Street

Ferndale, Michigan

June 29-July 1, 2010

Not to Scale

≈ 200 feet

≈ 380 feet
Figure No. 2

Site: Sampling Date:

USEPA Method 3A June 29-July 1, 2010

DTE Monroe Power Plant

Unit 3

BT Environmental Consulting Inc. 

2615 Wolcott 

Ferndale MI 48220

Teledine CO2 analyzer

Heated Sample Line

Flow Controller

Pump

Moisture Removal System

 Vent

Data Acquisition System, Laptop 

PC, & Pdaq Software

Calibration Line

M&C PMA100-L

O2

Analyzer

Calibration Gas

Mid High Zero
Figure No. 6

Site: Sampling Date:USEPA Method 23 Sampling Train June 29-July 1, 2010DTE Monroe Power PlantUnit 3

BT Environmental Cons2615 Wolcott Ferndale, Michigan 482

100 ml HPLC Water

Heated Filter Box

S-type pitot w/ thermocouple Heated probe with glass liner & nozzle

Meter Rig

Temp.

ProbeFilter

On

Off

-

+

00:00

1 2 3 4 5

Empty  
Appendix A 

Field and Computer Generated Raw Data and Field Notes 
BT Environmental Consulting

Isokinetic Run Sheet

Project No.: 10-3991.01 Probe # 9ft Pollutant D/F Points/Port 3 Start Finish Pre Post

Company DTE DGM # MB-5 Method 23 Total Points 12 0.00@15"

Location Monroe PP Rate (cfm) Run # 1 Time/pt (min) 40.0

Source Unit 3 Exhaust Delta ∆H@ 1.56 Date 6/29/10 Time/reading 5.0

Operator MS/JB Bws (%) 11.6 # of Ports 4 Total Run 480.0

Filter Number A-2 Condensate Volume 978 Cp 0.840 Ps (in Hg) 29.98 0.00@13"

Barometric 30.05 Silica Gel Weight Gain 72 DGM Y 1.012 Pm (in Hg) 30.05 Ref Temp 68

Static (in H2O) -0.95 Actual Dn (in) 0.205 O2 (%) 6.1 Ref Press 29.92

Stack Dia (in) 336 An (ft^2) 0.00023 CO2 (%) 13.9 Md 30.47 Stack Area (sf) 615.75

Stack Dia (ft) 28.00 Est.DH(in H2O) Ms 29.02 Act. Flow (cfm) 2,218,850 Must delete extra zeros in the Velocity column

Vmnstd 313.14 Preliminary dP (in H20) Total Vol.(cf) 0.0 Wet Ref Flow (cfm) 1,996,159

Moisture % 13.63 Preliminary Ts (oF) Est. Us (ft/s) 0.0 Dry Ref Flow (cfm) 1,764,605

Preliminary Tm (oF) Theor Dn (in) #DIV/0! Comments: "Data Entry Cells" 

Leak check loss: 0.161 "Calculated Cells Do Not Touch"

PT # Start Time End Time

Clock Time 

(24hr) DGM Vol. Delta P Stack Temp Meter In Meter Out

Desired Delta 

H

Actual 

Delta H

Probe Temp. 

(*F)

Filter Temp 

(*F)

Imp temp. 

(*F) Pump Vac.

Condenser 

Filter Temp 

(*F)

A1-1 0.0 5.0 8:40 665.82 1.10 128 89 89 1.39 1.38 246 251 66 6.5 63

A1-2 5.0 10.0 669.35 1.10 128 90 90 1.39 1.38 248 250 63 7.5 53

A1-3 10.0 15.0 672.70 1.10 129 91 90 1.39 1.38 250 250 63 7.5 52

A1-4 15.0 20.0 676.07 1.10 129 92 90 1.39 1.38 250 249 58 7.5 52

A1-5 20.0 25.0 679.56 1.10 128 94 91 1.40 1.39 250 251 58 7.5 52

A1-6 25.0 30.0 682.99 1.10 128 94 91 1.40 1.39 250 251 57 7.5 52

A1-7 30.0 35.0 686.48 1.10 128 95 91 1.40 1.39 250 250 57 7.5 53

A1-8 35.0 40.0 689.95 1.10 127 96 91 1.40 1.39 250 250 57 7.5 52

A2-1 40.0 45.0 693.44 1.00 128 96 91 1.28 1.27 249 250 57 7.5 50

A2-2 45.0 50.0 696.85 1.00 127 96 92 1.28 1.27 251 250 57 7.5 51

A2-3 50.0 55.0 700.20 1.00 128 97 92 1.28 1.27 251 250 57 7 50

A2-4 55.0 60.0 703.43 1.00 128 96 92 1.28 1.27 250 249 57 7.5 51

A2-5 60.0 65.0 706.81 1.00 128 96 92 1.28 1.27 251 250 58 7.5 52

A2-6 65.0 70.0 710.15 1.00 128 96 92 1.28 1.27 250 250 57 7.5 53

A2-7 70.0 75.0 713.45 1.00 128 96 92 1.28 1.27 250 250 58 7.5 54

A2-8 75.0 80.0 716.79 1.00 128 97 92 1.29 1.27 250 250 59 7.5 54

A3-1 80.0 85.0 720.05 0.90 127 97 92 1.16 1.14 250 250 59 7.5 53

A3-2 85.0 90.0 723.21 0.90 127 97 92 1.16 1.14 251 250 60 7 53

A3-3 90.0 95.0 726.42 0.90 128 97 93 1.16 1.14 250 249 60 7 52

A3-4 95.0 100.0 729.66 0.90 128 97 92 1.16 1.14 250 250 60 7 51

A3-5 100.0 105.0 732.76 0.85 128 97 93 1.10 1.08 251 250 60 7 51

A3-6 105.0 110.0 735.72 0.85 128 96 93 1.10 1.08 250 250 61 7 52

A3-7 110.0 115.0 738.73 0.87 128 97 93 1.13 1.1 250 250 61 7 53

A3-8 115.0 120.0 10:40 741.80 0.87 128 96 93 1.13 1.1 249 250 62 7 52

B1-1 120.0 125.0 10:53 744.86 1.10 128 92 92 1.43 1.39 251 251 66 8.5 67

B1-2 125.0 130.0 748.38 1.10 128 93 92 1.43 1.39 249 250 66 8.5 54

B1-3 130.0 135.0 751.82 1.10 128 94 92 1.43 1.39 249 250 66 8.5 54

B1-4 135.0 140.0 755.26 1.10 128 95 92 1.43 1.39 250 250 65 8.5 54

B1-5 140.0 145.0 758.74 1.10 129 95 92 1.44 1.39 250 249 65 8.5 55

B1-6 145.0 150.0 762.16 1.10 129 96 92 1.44 1.39 250 249 65 8.5 56

B1-7 150.0 155.0 765.67 1.10 128 96 92 1.44 1.39 249 249 66 8.5 57

B1-8 155.0 160.0 769.07 1.10 128 96 92 1.44 1.39 251 250 66 8.5 57

B2-1 160.0 165.0 772.56 1.00 128 97 92 1.31 1.27 251 251 65 8.5 58

B2-2 165.0 170.0 776.00 1.00 128 97 92 1.31 1.27 250 250 64 8.5 54

B2-3 170.0 175.0 779.30 0.98 128 97 92 1.29 1.24 250 250 64 8.5 54

B2-4 175.0 180.0 782.51 0.98 127 97 92 1.29 1.24 250 250 64 8.5 53

B2-5 180.0 185.0 785.91 1.00 128 97 93 1.32 1.27 250 249 63 8.5 59

B2-6 185.0 190.0 789.24 1.00 128 97 93 1.32 1.27 250 250 62 8 56

B2-7 190.0 195.0 792.60 0.97 128 97 93 1.28 1.23 250 250 63 8.5 53

B2-8 195.0 200.0 795.85 0.97 128 97 93 1.28 1.23 251 250 64 8.5 50

B3-1 200.0 205.0 799.14 1.00 128 97 93 1.32 1.27 246 250 64 8 54

B3-2 205.0 210.0 802.48 1.00 128 97 93 1.32 1.27 249 250 64 8 53

B3-3 210.0 215.0 805.82 0.95 128 97 93 1.26 1.21 250 250 64 8 54

B3-4 215.0 220.0 809.07 0.95 128 96 93 1.26 1.21 250 250 63 8 53

B3-5 220.0 225.0 812.32 0.95 128 97 93 1.26 1.21 250 252 63 8 53

B3-6 225.0 230.0 815.71 0.95 127 97 93 1.26 1.21 251 250 63 8 52

B3-7 230.0 235.0 818.80 1.00 128 97 93 1.33 1.27 249 250 63 8 55

B3-8 235.0 240.0 12:48 822.23 1.00 128 98 93 1.33 1.27 249 251 63 8 54

C1-1 240.0 245.0 13:06 825.48 1.10 128 94 93 1.47 1.39 249 250 61 9 61

C1-2 245.0 250.0 13:14 829.04 1.10 128 94 93 1.47 1.39 250 250 61 9 60

C1-3 250.0 255.0 13:19 832.47 1.10 128 93 93 1.47 1.39 249 250 62 8 57

C1-4 255.0 260.0 835.82 1.10 128 94 92 1.47 1.39 249 251 63 8 55

C1-5 260.0 265.0 839.44 1.10 129 94 92 1.48 1.39 249 249 63 8 53

C1-6 265.0 270.0 842.94 1.10 127 95 92 1.48 1.39 251 250 64 8 53

C1-7 270.0 275.0 846.43 1.10 128 95 92 1.48 1.39 250 251 65 8 54

C1-8 275.0 280.0 849.91 1.10 128 96 92 1.48 1.39 249 250 65 8 55

C2-1 280.0 285.0 853.35 1.10 128 96 92 1.48 1.39 250 250 66 8 59

C2-2 285.0 290.0 856.82 1.10 129 96 92 1.48 1.39 250 250 64 8 60

C2-3 290.0 295.0 860.28 1.10 129 96 92 1.49 1.39 251 250 66 8 60

C2-4 295.0 300.0 863.73 1.10 129 97 93 1.49 1.39 250 250 66 8 59

C2-5 300.0 305.0 867.21 1.00 128 97 93 1.35 1.27 250 249 65 8 59

C2-6 305.0 310.0 870.69 1.00 129 97 93 1.35 1.27 250 250 65 8 61

C2-7 310.0 315.0 873.91 1.10 129 97 93 1.49 1.39 249 248 64 8 60

C2-8 315.0 320.0 877.34 1.10 127 97 93 1.49 1.39 251 250 65 8 62

C3-1 320.0 325.0 880.83 0.96 128 97 93 1.30 1.22 250 250 64 8 64

C3-2 325.0 330.0 884.11 0.96 128 97 93 1.31 1.22 248 250 63 8 63

C3-3 330.0 335.0 887.37 0.98 128 97 93 1.34 1.24 250 250 64 7.5 59

C3-4 335.0 340.0 890.63 0.98 128 97 93 1.34 1.24 249 250 62 7.5 59

C3-5 340.0 345.0 893.94 0.98 128 97 94 1.34 1.24 249 248 61 7.5 58

C3-6 345.0 350.0 897.20 0.98 128 97 93 1.34 1.24 251 250 60 7.5 58

C3-7 350.0 355.0 900.50 0.95 128 9 93 1.30 1.21 249 249 61 7.5 60

C3-8 355.0 360.0 15:06 903.74 0.95 128 97 93 1.30 1.21 251 250 60 7.5 59

D1-1 360.0 365.0 15:49 907.11 1.10 128 93 93 1.51 1.39 247 250 66 7.5 64

D1-2 365.0 370.0 910.48 1.10 128 93 93 1.51 1.39 248 250 65 7.5 51

D1-3 370.0 375.0 913.93 1.10 128 93 92 1.51 1.39 250 249 65 7.5 50

D1-4 375.0 380.0 917.43 1.10 128 94 92 1.51 1.39 250 250 64 7.5 50

D1-5 380.0 385.0 920.83 1.20 127 95 92 1.65 1.52 250 250 64 7.5 48

D1-6 385.0 390.0 924.42 1.20 128 97 92 1.65 1.52 250 250 63 7.5 48

D1-7 390.0 395.0 928.04 1.10 127 97 92 1.52 1.4 250 250 62 8 48

D1-8 395.0 400.0 931.57 1.10 128 97 93 1.52 1.4 250 250 62 8 49

D2-1 400.0 405.0 935.07 1.10 128 97 93 1.52 1.4 249 250 62 7.5 49

D2-2 405.0 410.0 938.52 1.10 128 98 93 1.52 1.4 250 250 62 7.5 47

D2-3 410.0 415.0 942.05 1.10 128 98 93 1.52 1.4 251 250 63 7.5 47

D2-4 415.0 420.0 945.42 1.10 128 99 94 1.53 1.4 250 251 63 7.5 48

D2-5 420.0 425.0 948.92 1.10 128 100 94 1.53 1.4 251 250 62 7.5 47

D2-6 425.0 430.0 952.53 1.10 129 100 94 1.53 1.4 250 249 61 7.5 48

D2-7 430.0 435.0 955.97 1.10 129 100 94 1.53 1.4 250 251 61 7.5 48

D2-8 435.0 440.0 959.32 1.10 129 100 94 1.53 1.4 250 250 62 7.5 48

D3-1 440.0 445.0 962.83 1.00 129 100 94 1.40 1.27 251 250 61 7.5 48

D3-2 445.0 450.0 966.24 1.00 129 100 94 1.40 1.27 251 250 61 7.5 48

D3-3 450.0 455.0 969.59 1.10 129 100 95 1.54 1.4 250 250 61 7.5 48

D3-4 455.0 460.0 973.03 1.10 129 99 95 1.54 1.4 250 250 62 7.5 49

D3-5 460.0 465.0 976.55 1.00 128 100 95 1.40 1.27 250 250 61 7.5 49

D3-6 465.0 470.0 979.97 1.00 128 100 95 1.40 1.27 250 250 62 7.5 49

D3-7 470.0 475.0 983.38 1.00 128 100 95 1.40 1.27 249 250 62 7.5 51

D3-8 475.0 480.0 986.73 1.00 129 100 95 1.41 1.27 250 250 63 7.5 53

480.0 990.00

Leak Check
BT Environmental Consulting

Isokinetic Run Sheet

Project No.: 10-3991.01 Probe # 9ft Pollutant D/F Points/Port 12 Start Finish Pre Post

Company DTE DGM # MB-5 Method 23 Total Points 48 0.00@15" 0.00@14"

Location Monroe PP Rate (cfm) Run # 2 Time/pt (min) 15.0

Source Unit 3 Exhaust Delta ∆H@ 1.56 Date 6/30/10 Time/reading 5.0

Operator MS/JB Bws (%) 13.5 # of Ports 4 Total Run 720.0

Filter Number A-2 Condensate Volume 967 Cp 0.840 Ps (in Hg) 29.98

Barometric 30.05 Silica Gel Weight Gain 76 DGM Y 1.012 Pm (in Hg) 30.05 Ref Temp 68

Static (in H2O) -0.95 Actual Dn (in) 0.205 O2 (%) 6.15 Ref Press 29.92

Stack Dia (in) 336 An (ft^2) 0.00023 CO2 (%) 13.5 Md 30.41 Stack Area (sf) 615.75

Stack Dia (ft) 28.00 Est.DH(in H2O) Ms 28.73 Act. Flow (cfm) 2,233,649 Must delete extra zeros in the Velocity column

Vmnstd 309.91 Preliminary dP (in H20) Total Vol.(cf) 0.0 Wet Ref Flow (cfm) 2,009,651

Moisture % 13.67 Preliminary Ts (oF) Est. Us (ft/s) 0.0 Dry Ref Flow (cfm) 1,738,348

Preliminary Tm (oF) Theor Dn (in) #DIV/0! Comments: "Data Entry Cells" 

Leak check loss: 0.43 "Calculated Cells Do Not Touch"

PT # Start Time End Time

Clock 

Time 

(24hr) DGM Vol. ∆P Stack Temp Meter In Meter Out Desired Delta H

Actu

al 

Delta 

H

Probe Temp. 

(*F)

Filter Temp 

(*F)

Imp temp. 

(*F) Pump Vac.

Condenser 

Filter Temp 

(*F)

A1-1 0.0 5.0 7:43 12.98 1.10 128 86 86 1.34 1.37 249 250 66 6 55

A1-2 5.0 10.0 16.44 1.10 128 86 87 1.34 1.37 249 251 66 6.5 48

A1-3 10.0 15.0 19.82 1.10 128 87 87 1.34 1.38 250 250 62 6.5 48

A1-4 15.0 20.0 23.21 1.10 128 89 88 1.34 1.38 250 250 59 6.5 47

A1-5 20.0 25.0 26.62 1.10 127 89 87 1.34 1.38 250 250 57 6.5 47

A1-6 25.0 30.0 30.03 1.10 128 90 87 1.34 1.38 250 251 56 7 47

A1-7 30.0 35.0 33.47 1.00 127 91 87 1.22 1.26 250 250 57 7 48

A1-8 35.0 40.0 36.85 1.00 127 92 88 1.22 1.26 250 250 56 7 47

A2-1 40.0 45.0 40.10 1.10 128 92 88 1.35 1.38 250 250 57 7 47

A2-2 45.0 50.0 43.59 1.10 127 93 88 1.35 1.38 250 250 56 7 48

A2-3 50.0 55.0 47.03 1.10 128 93 88 1.35 1.38 249 250 56 7 47

A2-4 55.0 60.0 50.47 1.10 129 93 88 1.35 1.38 250 250 56 7 46

A2-5 60.0 65.0 53.94 1.00 129 93 88 1.23 1.26 251 250 56 7 46

A2-6 65.0 70.0 57.33 1.00 129 93 89 1.23 1.26 250 249 56 7 46

A2-7 70.0 75.0 60.55 1.00 129 94 89 1.23 1.26 251 251 56 7 47

A2-8 75.0 80.0 63.82 1.00 128 94 89 1.23 1.26 250 250 56 7 47

A3-1 80.0 85.0 67.14 0.92 128 94 89 1.14 1.16 250 250 56 7 48

A3-2 85.0 90.0 70.33 0.92 128 94 89 1.14 1.16 252 251 55 7 48

A3-3 90.0 95.0 73.52 0.94 127 94 89 1.16 1.19 250 250 55 7 47

A3-4 95.0 100.0 76.12 0.94 128 94 89 1.16 1.19 250 250 58 7 49

A3-5 100.0 105.0 79.93 0.92 128 94 90 1.14 1.16 250 250 58 7 50

A3-6 105.0 110.0 83.04 0.92 128 94 90 1.14 1.16 250 250 60 7 52

A3-7 110.0 115.0 86.20 0.92 128 94 90 1.14 1.16 249 250 61 7 51

A3-8 115.0 120.0 9:38 89.32 0.92 128 94 90 1.15 1.16 250 251 60 7 50

B1-1 120.0 125.0 10:00 92.74 1.10 128 90 89 1.37 1.34 250 251 66 7.5 59

B1-2 125.0 130.0 96.12 1.10 128 90 89 1.37 1.34 248 250 66 7.5 53

B1-3 130.0 135.0 99.54 1.10 128 90 89 1.37 1.34 249 249 65 7.5 54

B1-4 135.0 140.0 102.94 1.10 128 91 89 1.38 1.34 249 250 65 7.5 56

B1-5 140.0 145.0 106.35 1.10 127 92 88 1.38 1.35 251 250 65 7.5 57

B1-6 145.0 150.0 109.91 1.10 127 92 89 1.38 1.35 250 251 65 7.5 57

B1-7 150.0 155.0 113.16 1.10 127 93 89 1.38 1.35 251 250 64 7.5 59

B1-8 155.0 160.0 116.55 1.10 127 93 89 1.38 1.35 250 251 64 7.5 61

B2-1 160.0 165.0 119.95 1.00 128 93 89 1.26 1.23 250 249 64 7.5 61

B2-2 165.0 170.0 123.22 1.00 128 94 90 1.26 1.23 250 250 64 7.5 61

B2-3 170.0 175.0 126.47 1.00 128 94 89 1.26 1.23 250 249 64 7.5 60

B2-4 175.0 180.0 129.79 1.00 128 94 89 1.26 1.23 251 250 64 7.5 61

B2-5 180.0 185.0 133.05 0.98 128 94 89 1.24 1.2 251 250 63 7.5 59

B2-6 185.0 190.0 136.29 0.98 128 95 90 1.24 1.2 250 251 62 7 57

B2-7 190.0 195.0 139.49 0.98 128 95 90 1.24 1.2 250 250 62 7 55

B2-8 195.0 200.0 142.70 0.98 128 95 90 1.24 1.2 250 250 62 7 56

B3-1 200.0 205.0 145.94 0.95 127 95 90 1.21 1.17 246 250 63 7 59

B3-2 205.0 210.0 149.10 0.95 128 95 90 1.21 1.17 249 250 63 7 58

B3-3 210.0 215.0 152.22 0.92 128 95 90 1.17 1.13 251 250 62 7 59

B3-4 215.0 220.0 155.32 0.92 128 95 91 1.17 1.13 251 250 62 7 62

B3-5 220.0 225.0 158.45 0.95 129 95 91 1.21 1.17 250 250 62 7 61

B3-6 225.0 230.0 161.59 0.95 128 95 91 1.21 1.17 251 249 62 7 60

B3-7 230.0 235.0 164.75 0.92 129 95 91 1.18 1.13 250 249 64 7 62

B3-8 235.0 240.0 11:55 167.85 0.92 129 95 91 1.18 1.13 249 250 64 7 61

C1-1 240.0 245.0 12:23 171.16 1.10 128 90 90 1.41 1.35 247 247 65 6.5 61

C1-2 245.0 250.0 174.56 1.10 129 90 89 1.41 1.35 248 248 65 7 47

C1-3 250.0 255.0 177.98 1.10 128 91 89 1.41 1.35 248 248 65 7 48

C1-4 255.0 260.0 181.71 1.10 128 92 89 1.41 1.35 248 248 65 7 47

C1-5 260.0 265.0 184.83 1.10 128 93 89 1.42 1.35 249 249 63 7 47

C1-6 265.0 270.0 188.20 1.10 128 94 89 1.42 1.35 250 250 62 7 48

C1-7 270.0 275.0 191.60 1.10 128 94 89 1.42 1.35 250 250 62 7 48

C1-8 275.0 280.0 194.99 1.10 128 94 90 1.42 1.35 251 251 62 7 48

C2-1 280.0 285.0 198.40 1.10 129 94 90 1.42 1.35 250 250 63 7 48

C2-2 285.0 290.0 201.90 1.10 129 95 90 1.42 1.35 252 252 63 7 51

C2-3 290.0 295.0 205.19 1.10 128 95 90 1.42 1.35 254 254 64 7 54

C2-4 295.0 300.0 209.12 1.10 128 96 90 1.43 1.35 253 253 62 7 53

C2-5 300.0 305.0 212.20 1.10 128 96 90 1.43 1.35 255 255 60 7 5

C2-6 305.0 310.0 215.92 1.10 128 95 90 1.43 1.35 252 252 61 7 55

C2-7 310.0 315.0 219.01 1.00 127 95 91 1.30 1.23 255 255 62 7 55

C2-8 315.0 320.0 222.19 1.00 127 95 90 1.30 1.23 254 254 64 7 56

C3-1 320.0 325.0 225.49 0.98 128 96 91 1.28 1.21 253 253 64 6.5 55

C3-2 325.0 330.0 228.85 0.98 128 96 91 1.28 1.21 255 255 64 6.5 53

C3-3 330.0 335.0 232.02 0.95 128 96 91 1.24 1.17 249 249 64 6.5 53

C3-4 335.0 340.0 235.30 0.95 128 96 91 1.24 1.17 250 250 66 6 49

C3-5 340.0 345.0 238.43 0.95 129 96 91 1.24 1.17 252 252 66 6 53

C3-6 345.0 350.0 241.56 0.95 128 96 91 1.25 1.17 250 250 66 6 51

C3-7 350.0 355.0 244.72 0.97 128 96 91 1.27 1.19 249 249 64 6 50

C3-8 355.0 360.0 247.94 0.97 129 96 92 1.27 1.19 250 250 65 6 52

D1-1 360.0 365.0 14:40 251.31 1.20 129 91 91 1.58 1.47 251 251 66 8 53

D1-2 365.0 370.0 254.98 1.20 129 91 90 1.58 1.47 249 249 66 7.5 46

D1-3 370.0 375.0 258.51 1.20 128 92 90 1.58 1.47 250 250 64 7.5 45

D1-4 375.0 380.0 262.05 1.20 128 94 91 1.58 1.47 250 250 64 7 45

D1-5 380.0 385.0 265.55 1.10 127 94 91 1.45 1.35 251 251 61 7 45

D1-6 385.0 390.0 268.93 1.10 128 95 90 1.45 1.35 250 250 60 7 45

D1-7 390.0 395.0 272.35 1.20 128 95 90 1.59 1.47 251 251 59 7 44

D1-8 395.0 400.0 275.88 1.20 128 96 90 1.59 1.47 250 250 59 7 45

D2-1 400.0 405.0 279.44 1.10 128 96 90 1.46 1.35 250 250 59 7 44

D2-2 405.0 410.0 282.87 1.10 128 96 91 1.46 1.35 249 249 58 7 44

D2-3 410.0 415.0 286.32 1.10 128 96 91 1.46 1.35 249 249 58 7 44

D2-4 415.0 420.0 289.55 1.10 129 96 91 1.46 1.35 251 251 58 6.5 44

D2-5 420.0 425.0 293.06 1.10 129 96 91 1.47 1.35 251 251 58 7 44

D2-6 425.0 430.0 296.45 1.10 128 96 91 1.47 1.35 250 250 58 7 45

D2-7 430.0 435.0 299.93 1.10 128 95 91 1.47 1.35 250 250 59 7 45

D2-8 435.0 440.0 303.33 1.10 128 95 91 1.47 1.35 250 250 60 7 45

D3-1 440.0 445.0 306.76 1.00 128 95 91 1.34 1.23 250 250 60 7 44

D3-2 445.0 450.0 310.15 1.00 128 95 91 1.34 1.23 249 249 60 7 45

D3-3 450.0 455.0 313.32 1.00 128 95 91 1.34 1.23 250 250 59 7 45

D3-4 455.0 460.0 316.72 1.00 128 96 91 1.34 1.23 251 251 59 7 46

D3-5 460.0 465.0 319.60 0.98 128 96 91 1.32 1.21 250 250 60 7 45

D3-6 465.0 470.0 322.95 0.98 128 96 91 1.32 1.21 250 250 60 7 47

D3-7 470.0 475.0 326.20 0.98 128 97 91 1.32 1.21 249 249 61 7 49

D3-8 475.0 480.0 329.45 0.98 128 97 91 1.32 1.21 249 249 60 7 49

480.0 332.77

Leak Check
BT Environmental Consulting

Isokinetic Run Sheet

Project No.: 10-3991.01 Probe # 9ft Pollutant D/F Points/Port 12 Start Finish Pre Post

Company DTE DGM # MB-5 Method 23 Total Points 48

Location Monroe PP Rate (cfm) Run # 3 Time/pt (min) 15.0

Source Unit 3 Exhaust Delta ∆H@ 1.56 Date 7/1/10 Time/reading 5.0

Operator MS/JB Bws (%) 13.5 # of Ports 4 Total Run 720.0

Filter Number A-2 Condensate Volume 484 Cp 0.840 Ps (in Hg) 29.98

Barometric 30.05 Silica Gel Weight Gain 18 DGM Y 1.012 Pm (in Hg) 30.05 Ref Temp 68

Static (in H2O) -0.95 Actual Dn (in) 0.205 O2 (%) 6.15 Ref Press 29.92

Stack Dia (in) 336 An (ft^2) 0.00023 CO2 (%) 13.5 Md 30.41 Stack Area (sf) 615.75

Stack Dia (ft) 28.00 Est.DH(in H2O) Ms 28.73 Act. Flow (cfm) 2,266,816 Must delete extra zeros in the Velocity column

Vmnstd 311.76 Preliminary dP (in H20) Total Vol.(cf) 0.0 Wet Ref Flow (cfm) 2,037,975

Moisture % 7.05 Preliminary Ts (oF) Est. Us (ft/s) 0.0 Dry Ref Flow (cfm) 1,762,849

Preliminary Tm (oF) Theor Dn (in) #DIV/0! Comments: "Data Entry Cells" 

Leak check loss: 0.37 "Calculated Cells Do Not Touch"

PT # Start Time End Time

Clock Time 

(24hr) DGM Vol. Delta P Stack Temp Meter In Meter Out

Desired Delta 

H

Actual 

Delta H

Probe Temp. 

(*F)

Filter Temp 

(*F)

Imp temp. 

(*F) Pump Vac.

Condenser 

Filter Temp 

(*F)

A1-1 0.0 5.0 7:52 333.20 1.10 127 85 85 1.33 1.34 252 250 66 6 63

A1-2 5.0 10.0 336.69 1.10 128 87 86 1.33 1.34 252 250 66 6 63

A1-3 10.0 15.0 340.04 1.10 128 88 87 1.34 1.34 254 250 66 6 60

A1-4 15.0 20.0 343.44 1.10 127 90 87 1.34 1.34 250 250 65 6 57

A1-5 20.0 25.0 346.80 1.10 128 90 87 1.34 1.34 250 250 63 6 55

A1-6 25.0 30.0 350.01 1.10 128 91 87 1.34 1.34 250 250 62 6 54

A1-7 30.0 35.0 353.56 1.10 128 92 88 1.34 1.35 245 250 62 6 54

A1-8 35.0 40.0 356.93 1.10 128 93 88 1.34 1.35 252 250 62 6 53

A2-1 40.0 45.0 360.33 1.10 128 93 88 1.34 1.35 249 250 63 6 54

A2-2 45.0 50.0 363.69 1.10 128 93 88 1.35 1.35 251 250 62 6 55

A2-3 50.0 55.0 367.11 1.10 127 93 89 1.35 1.35 251 250 62 6 56

A2-4 55.0 60.0 370.53 1.10 128 94 89 1.35 1.35 250 250 62 6 53

A2-5 60.0 65.0 373.97 1.10 128 94 89 1.35 1.35 250 250 62 6 50

A2-6 65.0 70.0 376.40 1.10 128 95 89 1.35 1.35 250 250 62 6 50

A2-7 70.0 75.0 380.78 1.10 129 94 89 1.35 1.35 250 250 60 6 50

A2-8 75.0 80.0 384.17 1.10 129 94 89 1.36 1.35 250 250 61 6 51

A3-1 80.0 85.0 387.57 0.95 129 95 89 1.17 1.16 252 250 59 6 48

A3-2 85.0 90.0 390.82 0.95 129 95 90 1.17 1.16 251 250 58 6 47

A3-3 90.0 95.0 394.01 0.95 129 94 90 1.17 1.16 251 250 58 5 47

A3-4 95.0 100.0 397.18 0.95 129 94 90 1.18 1.16 250 250 59 5 47

A3-5 100.0 105.0 400.32 0.93 129 94 90 1.15 1.14 250 250 59 5 49

A3-6 105.0 110.0 403.42 0.93 129 94 90 1.15 1.14 251 251 59 5 50

A3-7 110.0 115.0 406.57 0.90 128 94 90 1.12 1.1 250 250 59 5 49

A3-8 115.0 120.0 409.64 0.90 128 94 90 1.12 1.1 251 250 60 5 50

B1-1 120.0 125.0 10:12 412.88 1.10 128 89 89 1.37 1.34 249 249 65 6 62

B1-2 125.0 130.0 416.30 1.10 128 89 88 1.37 1.34 248 250 65 6 57

B1-3 130.0 135.0 419.70 1.10 128 90 88 1.37 1.34 249 250 65 6 55

B1-4 135.0 140.0 423.20 1.10 128 92 88 1.37 1.34 251 250 64 6 52

B1-5 140.0 145.0 426.50 1.10 128 92 88 1.38 1.35 251 250 65 6 51

B1-6 145.0 150.0 429.98 1.10 128 93 88 1.38 1.35 250 250 65 6 51

B1-7 150.0 155.0 433.31 1.10 129 94 88 1.38 135 250 250 65 6 52

B1-8 155.0 160.0 436.69 1.10 128 94 89 1.38 1.35 249 250 65 6 52

B2-1 160.0 165.0 440.07 1.00 129 94 89 1.26 1.22 250 250 65 6 54

B2-2 165.0 170.0 443.30 1.00 129 95 89 1.26 1.22 251 250 64 6 54

B2-3 170.0 175.0 446.54 1.00 129 95 89 1.26 1.23 250 250 64 6 55

B2-4 175.0 180.0 449.74 1.00 129 95 89 1.26 1.23 250 250 64 6 57

B2-5 180.0 185.0 453.01 1.00 128 95 89 1.26 1.23 250 250 64 6 57

B2-6 185.0 190.0 456.23 1.00 128 95 89 1.26 1.23 251 250 64 6 58

B2-7 190.0 195.0 459.52 1.50 128 96 90 1.90 1.26 250 249 65 6 59

B2-8 195.0 200.0 462.80 1.50 128 96 90 1.90 1.29 250 250 64 6 57

B3-1 200.0 205.0 466.12 0.97 129 96 90 1.23 1.19 248 251 64 6 56

B3-2 205.0 210.0 469.32 0.97 128 96 90 1.23 1.19 250 250 62 6 53

B3-3 210.0 215.0 472.57 0.97 129 96 90 1.23 1.19 251 250 61 6 50

B3-4 215.0 220.0 475.69 0.97 129 96 90 1.23 1.19 251 250 62 6 51

B3-5 220.0 225.0 478.92 0.97 129 96 90 1.24 1.19 248 250 63 6 51

B3-6 225.0 230.0 482.07 0.97 129 96 90 1.24 1.19 251 250 63 6 57

B3-7 230.0 235.0 485.31 0.97 129 96 90 1.24 1.19 251 251 63 6 52

B3-8 235.0 240.0 488.55 0.97 128 96 90 1.24 1.19 250 250 63 6 52

C1-1 240.0 245.0 12:25 491.95 1.20 129 90 90 1.54 1.47 252 250 63 7 53

C1-2 245.0 250.0 495.51 1.20 129 92 90 1.54 1.47 252 250 63 7 53

C1-3 250.0 255.0 499.01 1.10 129 93 90 1.41 1.35 249 250 63 6.5 49

C1-4 255.0 260.0 502.42 1.10 128 94 90 1.41 1.35 250 250 64 6.5 50

C1-5 260.0 265.0 505.83 1.10 128 95 90 1.41 1.35 250 249 64 6.5 51

C1-6 265.0 270.0 509.27 1.10 128 96 90 1.42 1.35 250 250 64 6.5 51

C1-7 270.0 275.0 512.69 1.10 129 96 90 1.42 1.35 250 250 65 6.5 51

C1-8 275.0 280.0 516.10 1.10 128 96 90 1.42 1.35 250 250 65 6 50

C2-1 280.0 285.0 519.52 1.10 128 96 90 1.42 1.35 250 251 65 6 52

C2-2 285.0 290.0 522.93 1.10 128 96 91 1.42 1.35 250 250 64 6 54

C2-3 290.0 295.0 526.33 1.10 129 97 91 1.42 1.35 250 250 64 6 54

C2-4 295.0 300.0 529.73 1.10 129 97 91 1.43 1.35 250 250 64 6 54

C2-5 300.0 305.0 533.17 1.15 129 97 91 1.49 1.41 250 250 64 6 54

C2-6 305.0 310.0 536.65 1.15 129 97 91 1.49 1.41 251 249 64 6 53

C2-7 310.0 315.0 540.14 1.15 128 97 91 1.49 1.42 250 250 63 6.5 54

C2-8 315.0 320.0 543.65 1.15 129 97 91 1.50 1.42 250 250 63 6.5 56

C3-1 320.0 325.0 547.15 0.95 128 97 92 1.24 1.17 250 251 64 6 54

C3-2 325.0 330.0 550.03 0.95 129 97 92 1.24 1.17 250 250 64 6 55

C3-3 330.0 335.0 553.53 0.98 129 97 92 1.28 1.21 251 250 62 6 53

C3-4 335.0 340.0 556.76 0.98 129 97 92 1.28 1.21 250 250 63 6 54

C3-5 340.0 345.0 560.05 1.00 128 97 92 1.31 1.23 249 249 63 6 54

C3-6 345.0 350.0 563.24 1.00 128 97 92 1.31 1.23 249 250 63 6 54

C3-7 350.0 355.0 566.52 0.96 129 97 92 1.26 1.18 248 249 63 6 54

C3-8 355.0 360.0 569.75 0.96 129 97 92 1.26 1.18 249 250 62 6 54

D1-1 360.0 365.0 14:40 573.10 1.10 129 92 91 1.45 1.35 254 249 65 7 59

D1-2 365.0 370.0 576.49 1.10 128 92 91 1.45 1.35 248 249 64 7 53

D1-3 370.0 375.0 579.92 1.20 129 93 90 1.58 1.47 249 250 63 7 51

D1-4 375.0 380.0 583.33 1.20 129 94 90 1.58 1.47 250 250 63 7 51

D1-5 380.0 385.0 586.95 1.20 129 95 90 1.58 1.47 250 250 62 7 51

D1-6 385.0 390.0 590.44 1.20 129 96 90 1.59 1.47 250 250 61 7.5 52

D1-7 390.0 395.0 594.05 1.20 129 96 90 1.59 1.47 250 250 60 7.5 52

D1-8 395.0 400.0 597.59 1.20 129 96 91 1.59 1.47 250 250 59 7.5 54

D2-1 400.0 405.0 601.20 1.10 129 97 91 1.46 1.35 249 250 59 7.5 53

D2-2 405.0 410.0 604.61 1.10 129 97 91 1.46 1.35 251 250 59 7 50

D2-3 410.0 415.0 608.04 1.10 128 97 91 1.46 1.36 250 250 59 7 50

D2-4 415.0 420.0 611.49 1.10 128 97 91 1.46 1.36 250 250 58 7 51

D2-5 420.0 425.0 614.94 1.20 127 79 91 1.60 1.48 250 250 58 7 52

D2-6 425.0 430.0 618.51 1.20 128 97 91 1.60 1.48 249 251 59 7 52

D2-7 430.0 435.0 622.03 1.10 128 98 91 1.47 1.36 250 250 60 7.5 54

D2-8 435.0 440.0 625.47 1.10 128 98 92 1.47 1.36 250 250 60 7.5 55

D3-1 440.0 445.0 628.94 1.00 128 98 91 1.34 1.23 252 250 62 7.5 56

D3-2 445.0 450.0 632.27 1.00 129 98 92 1.34 1.23 251 250 62 7.5 56

D3-3 450.0 455.0 635.55 1.00 129 98 92 1.34 1.23 250 250 63 7.5 54

D3-4 455.0 460.0 638.83 1.00 129 98 92 1.34 1.23 250 250 64 7 53

D3-5 460.0 465.0 642.09 1.00 129 98 92 1.34 1.23 250 250 64 7 55

D3-6 465.0 470.0 645.38 1.00 129 98 93 1.34 1.23 250 250 65 7 57

D3-7 470.0 475.0 648.62 1.00 129 98 93 1.35 1.23 250 250 66 7 57

D3-8 475.0 480.0 651.90 1.00 129 98 93 1.35 1.23 250 250 66 7 57

480.0 655.16

Leak Check




















Appendix B 

Calibration Data 
METHOD 5 DRY GAS METER CALIBRATION USING CRITICAL ORIFICES

1) Select three critical orifices to calibrate the dry gas meter which bracket the expected operating range.2) Record barometric pressure before and after calibration procedure.3) Run at tested vacuum (from Orifice Calibration Report), for a period of time

necessary to achieve a minimum total volume of 5 cubic feet.

4) Record data and information in the GREEN cells, YELLOW cells are calculated.

INITIAL FINAL AVG (Pbar)

DATE: 4/13/2010 METER SERIAL #: 1672 BAROMETRIC PRESSURE (in Hg): 30.44 30.52 30.48 

METER PART #: MB5 CRITICAL ORIFICE SET SERIAL #: 1447 

K' TESTED TEMPERATURES °F ELAPSED

FACTOR VACUUM DGM READINGS (FT3) AMBIENT DGM INLET DGM OUTLET DGM TIME (MIN) DGM ΔH (1) 

ORIFICE # RUN # (AVG) (in Hg) INITIAL FINAL NET (Vm) INITIAL FINAL INITIAL FINAL AVG θ (in H2O) Vm (STD) Vcr 

1 0.8778 16 746.545 753.315 6.770 60 69 74 67 68 69.5 6.00 3.8 6.9415 7.2 0.8778 16 753.315 760.102 6.787 60 74 76 68 69 71.75 6.00 3.8 6.9295 7.3 0.8778 16 760.102 766.915 6.813 60 76 77 69 70 73 6.00 3.8 6.9397 7.1 0.5057 16 729.0 734.830 5.830 60 65 67 65 65 65.5 9.00 1.25 5.9865 6.2 0.5057 16 734.830 740.70 5.870 60 67 69 65 66 66.75 9.00 1.25 6.0133 6.3 0.5057 16 740.70 746.545 5.845 60 69 71 66 67 68.25 9.00 1.25 5.9706 6.1 0.3367 16 766.915 772.210 5.295 60 77 75 70 70 73 12.00 0.54 5.3514 5.2 0.3367 16 772.210 777.540 5.330 60 75 75 70 71 72.75 12.00 0.54 5.3893 5.3 0.3367 16 777.540 782.850 5.310 60 75 75 71 71 73 12.00 0.54 5.3666 5.

AVERAGE DRY GAS METER CALIBRATION FACT

AVERAG

(1) = Net volume of gas sample passed through DGM, corrected to standard conditions

K1 = 17.64 oR/in. Hg (English), 0.3858 oK/mm Hg (Metric)

Tm = Absolute DGM avg. temperature (oR - English, oK - Metric) ΔH@ = 0.

Vcr

(2) = Volume of gas sample passed through the critical orifice, corrected to standard conditions

Tamb = Absolute ambient temperature (oR - English, oK - Metric)

K' = Average K' factor from Critical Orifice Calibration

(3) = DGM calibration factor

321812

ENVIRONMENTAL 

USING THE CRITICAL ORIFICES AS CALIBRATION STANDARDS:The following equations are used to calculate the standard volumes of air passed through the DGM, Vm (std), and the critical 

orifice, Vcr (std), and the DGM calibration factor, Y. These equations are automatically calculated in the spreadsheet above.

(

Tm

Pbar

H Vm std

K Vm ( /13.6) ( ) 1

+ Δ = ∗ ∗

Tamb

Pbar Vcr std

K ∗ Θ ( ) = '∗

( )

( )

std

std

Vm

Vcr

Y =
METHOD 5 DRY GAS METER CALIBRATION USING CRITICAL ORIFICES

1) Select three critical orifices to calibrate the dry gas meter which bracket the expected operating range.2) Record barometric pressure before and after calibration procedure.3) Run at tested vacuum (from Orifice Calibration Report), for a period of time

necessary to achieve a minimum total volume of 5 cubic feet.

4) Record data and information in the GREEN cells, YELLOW cells are calculated.

INITIAL FINAL AVG (Pbar)

DATE: 7/6/2010 METER SERIAL #: 1672 BAROMETRIC PRESSURE (in Hg): 30.07 30.09 30.08 

METER PART #: MB5 CRITICAL ORIFICE SET SERIAL #: 1447 

K' TESTED TEMPERATURES °F ELAPSED

FACTOR VACUUM DGM READINGS (FT3) AMBIENT DGM INLET DGM OUTLET DGM TIME (MIN) DGM ΔH (1) 

ORIFICE # RUN # (AVG) (in Hg) INITIAL FINAL NET (Vm) INITIAL FINAL INITIAL FINAL AVG θ (in H2O) Vm (STD) Vcr 

1 0.8778 16 655.60 664.810 9.210 81 84 89 84 85 85.5 8.00 3.8 9.0470 9.2 0.8778 16 664.810 671.708 6.898 81 89 92 85 86 88 6.00 3.8 6.7450 6.3 0.8778 16 671.708 678.630 6.922 81 92 93 86 86 89.25 6.00 3.8 6.7530 6.1 0.5057 16 694.835 701.495 6.660 81 91 92 88 89 90 10.00 1.25 6.4485 6.2 0.5057 16 701.495 707.483 5.988 81 92 93 89 89 90.75 9.00 1.25 5.7899 5.3 0.5057 16 707.483 713.480 5.997 81 93 93 89 90 91.25 9.00 1.25 5.7934 5.1 0.3367 16 678.630 684.030 5.40 81 87 89 87 87 87.5 12.00 0.54 5.2433 5.2 0.3367 16 684.030 689.437 5.407 81 89 91 87 88 88.75 12.00 0.54 5.2381 5.3 0.3367 16 689.437 694.835 5.398 81 91 91 88 88 89.5 12.00 0.54 5.2223 5.

AVERAGE DRY GAS METER CALIBRATION FACT

AVERAG

(1) = Net volume of gas sample passed through DGM, corrected to standard conditions

K1 = 17.64 oR/in. Hg (English), 0.3858 oK/mm Hg (Metric)

Tm = Absolute DGM avg. temperature (oR - English, oK - Metric) ΔH@ = 0.

Vcr

(2) = Volume of gas sample passed through the critical orifice, corrected to standard conditions

Tamb = Absolute ambient temperature (oR - English, oK - Metric)

K' = Average K' factor from Critical Orifice Calibration

(3) = DGM calibration factor

321812

ENVIRONMENTAL 

USING THE CRITICAL ORIFICES AS CALIBRATION STANDARDS:The following equations are used to calculate the standard volumes of air passed through the DGM, Vm (std), and the critical 

orifice, Vcr (std), and the DGM calibration factor, Y. These equations are automatically calculated in the spreadsheet above.

(

Tm

Pbar

H Vm std

K Vm ( /13.6) ( ) 1

+ Δ = ∗ ∗

Tamb

Pbar Vcr std

K ∗ Θ ( ) = '∗

( )

( )

std

std

Vm

Vcr

Y =








Appendix C 

RAW CEM Data 
Appendix D 

Laboratory Analytical Results 
Site: DTE MONROE ICR TESTING 

Your C.O.C. #: n/a

Attention: Tom Snyder

BT Environmental Consulting

2615 Wolcott St.

Ferndale, MI

USA 48220

Report Date: 2010/07/28

CERTIFICATE OF ANALYSIS

MAXXAM JOB #: B089667

Received: 2010/07/08, 11:30

Sample Matrix: Stack Sampling Train

# Samples Received: 4

Date Date Method

Analyses Quantity Extracted Analyzed Laboratory Method Reference

Dioxins/Furans in Air (Method 23) (1 ) 4 2010/07/10 2010/07/20 BRL SOP-00404 EPA1613Bmod(M23/23A)

PCB Congeners in Air (1668A) 4 2010/07/10 2010/07/26 BRL SOP-00408, 409 EPA 1668A (0010) mod

* RPDs calculated using raw data. The rounding of final results may result in the apparent difference.

(1) This test was performed in Maxxam Mississauga under Maxxam Burlington SCC Accreditation

U = Undetected at the limit of quantitation.

J = Estimated concentration between the EDL & RDL.

B = Blank Contamination.

Q = One or more quality control criteria failed.

Encryption Key

Please direct all questions regarding this Certificate of Analysis to your Project Manager.

LINA BARRETO, Project Manager

Email: Lina.Barreto@maxxamanalytics.com

Phone# (905) 817-5700

====================================================================

Maxxam has procedures in place to guard against improper use of the electronic signature and have the required "signatories", as per section

5.10.2 of ISO/IEC 17025:2005(E), signing the reports. For Service Group specific validation please refer to the Validation Signature Page.

Total cover pages: 1

Maxxam Analytics International Corporation o/a Maxxam Analytics Burlington:5555 North Service Road, Burlington, Ontario L7L 5H7 Telephone(905) 332-8788 Fax(905) 332-9169

Page 1 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

RESULTS OF ANALYSES OF STACK SAMPLING TRAIN

Maxxam ID G K 9 3 7 6

Sampling Date 2010/06/29

18:00

COC Number n/a TOXIC EQUIVALENCY # of

 U n i t s F.BLANK-DTE EDL RDL TEF (2005 WHO) TEQ(DL) I s o m e r s QC Batch

MONROE-M23

33'44'-TetraCB-(77) ng 0.014 U 0.014 0.30 0.00010 0.0000014 2202679

344'5-TetraCB-(81) ng 0.014 U 0.014 0.30 0.00030 0.0000042 2202679

233'44'-PentaCB-(105) ng 0.013 U ( 1 ) 0.013 0.30 0.000030 0.00000039 2202679

2344'5-PentaCB-(114) ng 0.0094 U 0.0094 0.30 0.000030 0.00000028 2202679

23'44'5-PentaCB-(118) ng 0.032 U ( 1 ) 0.032 0.30 0.000030 0.00000096 2202679

23'44'5'-PentaCB-(123) ng 0.0096 U 0.0096 0.30 0.000030 0.00000029 2202679

33'44'5-PentaCB-(126) ng 0.0094 U 0.0094 0.30 0.10 0.00094 2202679

HexaCB-(156)+(157) ng 0.0098 U 0.0098 0.60 0.000030 0.00000029 2202679

23'44'55'-HexaCB-(167) ng 0.0097 U 0.0097 0.30 0.000030 0.00000029 2202679

33'44'55'-HexaCB-(169) ng 0.0099 U 0.0099 0.30 0.030 0.00030 2202679

233'44'55'-HeptaCB-(189) ng 0.014 U 0.014 0.30 0.000030 0.00000042 2202679

TOTAL TOXIC EQUIVALENCY ng 0.0012

Surrogate Recovery (%)

C13-233'44'55'-HeptaCB-(189) % 138 2202679

C13-233'44'5-HexaCB-(156) % 130 2202679

C13-233'44'5'-HexaCB-(157) % 130 2202679

C13-233'44'-PentaCB-(105) % 145 2202679

C13-23'44'55'-HexaCB-(167) % 138 2202679

C13-2344'5-PentaCB-(114) % 137 2202679

C13-23'44'5-PentaCB-(118) % 141 2202679

C13-2'344'5-PentaCB-(123) % 140 2202679

C13-33'44'55'-HexaCB-(169) % 136 2202679

C13-33'44'5-PentaCB-(126) % 153 ( 2 ) 2202679

C13-33'44'-TetraCB-(77) % 126 2202679

C13-344'5-TetraCB-(81) % 126 2202679

N/A = Not Applicable

RDL = Reportable Detection Limit

EDL = Estimated Detection Limit

QC Batch = Quality Control Batch

TEF = Toxic Equivalency Factor, TEQ = Toxic Equivalency Quotient,

The Total Toxic Equivalency (TEQ) value reported is the sum of Toxic Equivalent Quotients for the congeners tested.

WHO(2005): The 2005 World Health Organization, Human and Mammalian Toxic Equivalency Factors for Dioxins and

Dioxin-like Compounds

( 1 ) EMPC / NDR - Peak detected does not meet ratio criteria and has resulted in an elevated detection limit.

( 2 ) Recovery or RPD for this parameter is outside control limits. The overall quality control for this analysis meets

acceptability criteria.

Page 2 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

RESULTS OF ANALYSES OF STACK SAMPLING TRAIN

Maxxam ID G K 9 3 7 7

Sampling Date 2010/06/29

18:00

COC Number n/a TOXIC EQUIVALENCY # of

 U n i t s RUN 1-DTE EDL RDL TEF (2005 WHO) TEQ(DL) I s o m e r s QC Batch

MONROE-M23

33'44'-TetraCB-(77) ng 0.081 J 0.036 0.30 0.00010 0.0000081 2202679

344'5-TetraCB-(81) ng 0.037 U 0.037 0.30 0.00030 0.000011 2202679

233'44'-PentaCB-(105) ng 0.24 J 0.012 0.30 0.000030 0.0000072 2202679

2344'5-PentaCB-(114) ng 0.019 J 0.012 0.30 0.000030 0.00000057 2202679

23'44'5-PentaCB-(118) ng 0.68 0.011 0.30 0.000030 0.000020 2202679

23'44'5'-PentaCB-(123) ng 0.012 U 0.012 0.30 0.000030 0.00000036 2202679

33'44'5-PentaCB-(126) ng 0.012 U 0.012 0.30 0.10 0.0012 2202679

HexaCB-(156)+(157) ng 0.043 J 0.011 0.60 0.000030 0.0000013 2202679

23'44'55'-HexaCB-(167) ng 0.015 U ( 1 ) 0.015 0.30 0.000030 0.00000045 2202679

33'44'55'-HexaCB-(169) ng 0.011 U 0.011 0.30 0.030 0.00033 2202679

233'44'55'-HeptaCB-(189) ng 0.016 U 0.016 0.30 0.000030 0.00000048 2202679

TOTAL TOXIC EQUIVALENCY ng 0.0016

Surrogate Recovery (%)

C13-233'44'55'-HeptaCB-(189) % 143 2202679

C13-233'44'5-HexaCB-(156) % 125 2202679

C13-233'44'5'-HexaCB-(157) % 125 2202679

C13-233'44'-PentaCB-(105) % 132 2202679

C13-23'44'55'-HexaCB-(167) % 126 2202679

C13-2344'5-PentaCB-(114) % 127 2202679

C13-23'44'5-PentaCB-(118) % 134 2202679

C13-2'344'5-PentaCB-(123) % 130 2202679

C13-33'44'55'-HexaCB-(169) % 127 2202679

C13-33'44'5-PentaCB-(126) % 141 2202679

C13-33'44'-TetraCB-(77) % 132 2202679

C13-344'5-TetraCB-(81) % 131 2202679

N/A = Not Applicable

RDL = Reportable Detection Limit

EDL = Estimated Detection Limit

QC Batch = Quality Control Batch

TEF = Toxic Equivalency Factor, TEQ = Toxic Equivalency Quotient,

The Total Toxic Equivalency (TEQ) value reported is the sum of Toxic Equivalent Quotients for the congeners tested.

WHO(2005): The 2005 World Health Organization, Human and Mammalian Toxic Equivalency Factors for Dioxins and

Dioxin-like Compounds

( 1 ) EMPC / NDR - Peak detected does not meet ratio criteria and has resulted in an elevated detection limit.

Page 3 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

RESULTS OF ANALYSES OF STACK SAMPLING TRAIN

Maxxam ID G K 9 3 7 8

Sampling Date 2010/06/30

18:00

COC Number n/a TOXIC EQUIVALENCY # of

 U n i t s RUN 2-DTE EDL RDL TEF (2005 WHO) TEQ(DL) I s o m e r s QC Batch

MONROE-M23

33'44'-TetraCB-(77) ng 0.088 J 0.015 0.30 0.00010 0.0000088 2202679

344'5-TetraCB-(81) ng 0.048 U ( 1 ) 0.048 0.30 0.00030 0.000014 2202679

233'44'-PentaCB-(105) ng 0.24 J 0.0090 0.30 0.000030 0.0000072 2202679

2344'5-PentaCB-(114) ng 0.022 J 0.0091 0.30 0.000030 0.00000066 2202679

23'44'5-PentaCB-(118) ng 0.72 0.0087 0.30 0.000030 0.000022 2202679

23'44'5'-PentaCB-(123) ng 0.0092 U 0.0092 0.30 0.000030 0.00000028 2202679

33'44'5-PentaCB-(126) ng 0.0091 U 0.0091 0.30 0.10 0.00091 2202679

HexaCB-(156)+(157) ng 0.051 J 0.011 0.60 0.000030 0.0000015 2202679

23'44'55'-HexaCB-(167) ng 0.021 J 0.010 0.30 0.000030 0.00000063 2202679

33'44'55'-HexaCB-(169) ng 0.011 U 0.011 0.30 0.030 0.00033 2202679

233'44'55'-HeptaCB-(189) ng 0.016 U 0.016 0.30 0.000030 0.00000048 2202679

TOTAL TOXIC EQUIVALENCY ng 0.0013

Surrogate Recovery (%)

C13-233'44'55'-HeptaCB-(189) % 143 2202679

C13-233'44'5-HexaCB-(156) % 126 2202679

C13-233'44'5'-HexaCB-(157) % 126 2202679

C13-233'44'-PentaCB-(105) % 134 2202679

C13-23'44'55'-HexaCB-(167) % 125 2202679

C13-2344'5-PentaCB-(114) % 129 2202679

C13-23'44'5-PentaCB-(118) % 133 2202679

C13-2'344'5-PentaCB-(123) % 132 2202679

C13-33'44'55'-HexaCB-(169) % 129 2202679

C13-33'44'5-PentaCB-(126) % 140 2202679

C13-33'44'-TetraCB-(77) % 127 2202679

C13-344'5-TetraCB-(81) % 125 2202679

N/A = Not Applicable

RDL = Reportable Detection Limit

EDL = Estimated Detection Limit

QC Batch = Quality Control Batch

TEF = Toxic Equivalency Factor, TEQ = Toxic Equivalency Quotient,

The Total Toxic Equivalency (TEQ) value reported is the sum of Toxic Equivalent Quotients for the congeners tested.

WHO(2005): The 2005 World Health Organization, Human and Mammalian Toxic Equivalency Factors for Dioxins and

Dioxin-like Compounds

( 1 ) EMPC / NDR - Peak detected does not meet ratio criteria and has resulted in an elevated detection limit.

Page 4 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

RESULTS OF ANALYSES OF STACK SAMPLING TRAIN

Maxxam ID G K 9 3 7 9

Sampling Date 2010/07/01

18:00

COC Number n/a TOXIC EQUIVALENCY # of

 U n i t s RUN 3-DTE EDL RDL TEF (2005 WHO) TEQ(DL) I s o m e r s QC Batch

MONROE-M23

33'44'-TetraCB-(77) ng 0.065 J 0.018 0.30 0.00010 0.0000065 2202679

344'5-TetraCB-(81) ng 0.045 U ( 1 ) 0.045 0.30 0.00030 0.000014 2202679

233'44'-PentaCB-(105) ng 0.19 J 0.0086 0.30 0.000030 0.0000057 2202679

2344'5-PentaCB-(114) ng 0.014 J 0.0087 0.30 0.000030 0.00000042 2202679

23'44'5-PentaCB-(118) ng 0.54 0.0083 0.30 0.000030 0.000016 2202679

23'44'5'-PentaCB-(123) ng 0.0088 U 0.0088 0.30 0.000030 0.00000026 2202679

33'44'5-PentaCB-(126) ng 0.0087 U 0.0087 0.30 0.10 0.00087 2202679

HexaCB-(156)+(157) ng 0.045 J 0.010 0.60 0.000030 0.0000014 2202679

23'44'55'-HexaCB-(167) ng 0.019 J 0.010 0.30 0.000030 0.00000057 2202679

33'44'55'-HexaCB-(169) ng 0.010 U 0.010 0.30 0.030 0.00030 2202679

233'44'55'-HeptaCB-(189) ng 0.013 U 0.013 0.30 0.000030 0.00000039 2202679

TOTAL TOXIC EQUIVALENCY ng 0.0012

Surrogate Recovery (%)

C13-233'44'55'-HeptaCB-(189) % 132 2202679

C13-233'44'5-HexaCB-(156) % 125 2202679

C13-233'44'5'-HexaCB-(157) % 125 2202679

C13-233'44'-PentaCB-(105) % 130 2202679

C13-23'44'55'-HexaCB-(167) % 121 2202679

C13-2344'5-PentaCB-(114) % 125 2202679

C13-23'44'5-PentaCB-(118) % 129 2202679

C13-2'344'5-PentaCB-(123) % 126 2202679

C13-33'44'55'-HexaCB-(169) % 128 2202679

C13-33'44'5-PentaCB-(126) % 135 2202679

C13-33'44'-TetraCB-(77) % 127 2202679

C13-344'5-TetraCB-(81) % 131 2202679

N/A = Not Applicable

RDL = Reportable Detection Limit

EDL = Estimated Detection Limit

QC Batch = Quality Control Batch

TEF = Toxic Equivalency Factor, TEQ = Toxic Equivalency Quotient,

The Total Toxic Equivalency (TEQ) value reported is the sum of Toxic Equivalent Quotients for the congeners tested.

WHO(2005): The 2005 World Health Organization, Human and Mammalian Toxic Equivalency Factors for Dioxins and

Dioxin-like Compounds

( 1 ) EMPC / NDR - Peak detected does not meet ratio criteria and has resulted in an elevated detection limit.

Page 5 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

DIOXINS AND FURANS BY HRMS (STACK SAMPLING TRAIN)

Maxxam ID G K 9 3 7 6

Sampling Date 2010/06/29

18:00

COC Number n/a TOXIC EQUIVALENCY # of

 U n i t s F.BLANK-DTE EDL RDL TEF (2005 WHO) TEQ(DL) I s o m e r s QC Batch

MONROE-M23

2,3,7,8-Tetra CDD * pg 1.9 U 1.9 30 1.00 1.90 2209116

1,2,3,7,8-Penta CDD pg 2.0 U 2.0 30 1.00 2.00 2209116

1,2,3,4,7,8-Hexa CDD pg 1.7 U 1.7 30 0.100 0.170 2209116

1,2,3,6,7,8-Hexa CDD pg 1.8 U 1.8 30 0.100 0.180 2209116

1,2,3,7,8,9-Hexa CDD pg 1.6 U 1.6 30 0.100 0.160 2209116

1,2,3,4,6,7,8-Hepta CDD pg 1.6 U 1.6 30 0.0100 0.0160 2209116

1,2,3,4,6,7,8,9-Octa CDD pg 14 U ( 1 ) 14 300 0.000300 0.00420 2209116

Total Tetra CDD pg 3.2 U ( 2 ) 3.2 30 2209116

Total Penta CDD pg 2.4 U ( 2 ) 2.4 30 2209116

Total Hexa CDD pg 8.4 U ( 2 ) 8.4 30 2209116

Total Hepta CDD pg 1.6 U 1.6 30 2209116

2,3,7,8-Tetra CDF ** pg 3.2 J 1.9 30 0.100 0.320 2209116

1,2,3,7,8-Penta CDF pg 1.8 U 1.8 30 0.0300 0.0540 2209116

2,3,4,7,8-Penta CDF pg 2.6 J 1.8 30 0.300 0.780 2209116

1,2,3,4,7,8-Hexa CDF pg 1.6 U 1.6 30 0.100 0.160 2209116

1,2,3,6,7,8-Hexa CDF pg 1.5 U 1.5 30 0.100 0.150 2209116

2,3,4,6,7,8-Hexa CDF pg 1.7 U 1.7 30 0.100 0.170 2209116

1,2,3,7,8,9-Hexa CDF pg 1.8 U 1.8 30 0.100 0.180 2209116

1,2,3,4,6,7,8-Hepta CDF pg 1.5 U 1.5 30 0.0100 0.0150 2209116

1,2,3,4,7,8,9-Hepta CDF pg 1.8 U 1.8 30 0.0100 0.0180 2209116

1,2,3,4,6,7,8,9-Octa CDF pg 3.6 U 3.6 300 0.000300 0.00108 2209116

Total Tetra CDF pg 3.2 J 1.9 30 2209116

Total Penta CDF pg 2.6 J 1.8 30 2209116

Total Hexa CDF pg 1.6 U 1.6 30 2209116

Total Hepta CDF pg 1.6 U 1.6 30 2209116

N/A = Not Applicable

RDL = Reportable Detection Limit

EDL = Estimated Detection Limit

QC Batch = Quality Control Batch

* CDD = Chloro Dibenzo-p-Dioxin, ** CDF = Chloro Dibenzo-p-Furan

TEF = Toxic Equivalency Factor, TEQ = Toxic Equivalency Quotient,

The Total Toxic Equivalency (TEQ) value reported is the sum of Toxic Equivalent Quotients for the congeners tested.

WHO(2005): The 2005 World Health Organization, Human and Mammalian Toxic Equivalency Factors for Dioxins and

Dioxin-like Compounds

( 1 ) RT > 3 seconds - PCDD/DF analysis - Peak detected exceeds expected retention time (from internal standard) by

greater than 3 seconds.

( 2 ) EMPC / NDR - Peak detected does not meet ratio criteria and has resulted in an elevated detection limit.

Page 6 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

DIOXINS AND FURANS BY HRMS (STACK SAMPLING TRAIN)

Maxxam ID G K 9 3 7 6

Sampling Date 2010/06/29

18:00

COC Number n/a TOXIC EQUIVALENCY # of

 U n i t s F.BLANK-DTE EDL RDL TEF (2005 WHO) TEQ(DL) I s o m e r s QC Batch

MONROE-M23

TOTAL TOXIC EQUIVALENCY pg 6 . 2 8

Surrogate Recovery (%)

C13-1234678 HeptaCDD * % 93 2209116

C13-1234678 HeptaCDF ** % 101 2209116

C13-123478 HexaCDD % 104 2209116

C13-123478 HexaCDF % 99 2209116

C13-1234789 HeptaCDF % 86 2209116

C13-123678 HexaCDD % 96 2209116

C13-123678 HexaCDF % 95 2209116

C13-12378 PentaCDD % 74 2209116

C13-12378 PentaCDF % 68 2209116

C13-123789 HexaCDF % 88 2209116

C13-23478 PentaCDF % 107 2209116

C13-2378 TetraCDD % 50 2209116

C13-2378 TetraCDF % 45 2209116

C13-Octachlorodibenzo-p-Dioxin % 75 2209116

Cl37-2378 TetraCDD % 103 2209116

N/A = Not Applicable

RDL = Reportable Detection Limit

EDL = Estimated Detection Limit

QC Batch = Quality Control Batch

* CDD = Chloro Dibenzo-p-Dioxin, ** CDF = Chloro Dibenzo-p-Furan

TEF = Toxic Equivalency Factor, TEQ = Toxic Equivalency Quotient,

The Total Toxic Equivalency (TEQ) value reported is the sum of Toxic Equivalent Quotients for the congeners tested.

WHO(2005): The 2005 World Health Organization, Human and Mammalian Toxic Equivalency Factors for Dioxins and

Dioxin-like Compounds

Page 7 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

DIOXINS AND FURANS BY HRMS (STACK SAMPLING TRAIN)

Maxxam ID G K 9 3 7 7

Sampling Date 2010/06/29

18:00

COC Number n/a TOXIC EQUIVALENCY # of

 U n i t s RUN 1-DTE EDL RDL TEF (2005 WHO) TEQ(DL) I s o m e r s QC Batch

MONROE-M23

2,3,7,8-Tetra CDD * pg 2.1 U 2.1 30 1.00 2.10 2209116

1,2,3,7,8-Penta CDD pg 1.6 U 1.6 30 1.00 1.60 2209116

1,2,3,4,7,8-Hexa CDD pg 1.6 U 1.6 30 0.100 0.160 2209116

1,2,3,6,7,8-Hexa CDD pg 1.6 U 1.6 30 0.100 0.160 2209116

1,2,3,7,8,9-Hexa CDD pg 1.5 U 1.5 30 0.100 0.150 2209116

1,2,3,4,6,7,8-Hepta CDD pg 3.4 J 1.9 30 0.0100 0.0340 2209116

1,2,3,4,6,7,8,9-Octa CDD pg 19.9 J 4.0 300 0.000300 0.00597 2209116

Total Tetra CDD pg 2.1 U 2.1 30 2209116

Total Penta CDD pg 11 U ( 1 ) 11 30 2209116

Total Hexa CDD pg 11 U ( 1 ) 11 30 2209116

Total Hepta CDD pg 3.4 J 1.9 30 2209116

2,3,7,8-Tetra CDF ** pg 4.6 J 1.7 30 0.100 0.460 2209116

1,2,3,7,8-Penta CDF pg 1.8 U 1.8 30 0.0300 0.0540 2209116

2,3,4,7,8-Penta CDF pg 2.9 J 1.7 30 0.300 0.870 2209116

1,2,3,4,7,8-Hexa CDF pg 1.6 U 1.6 30 0.100 0.160 2209116

1,2,3,6,7,8-Hexa CDF pg 1.5 U 1.5 30 0.100 0.150 2209116

2,3,4,6,7,8-Hexa CDF pg 1.8 U 1.8 30 0.100 0.180 2209116

1,2,3,7,8,9-Hexa CDF pg 1.8 U 1.8 30 0.100 0.180 2209116

1,2,3,4,6,7,8-Hepta CDF pg 1.6 U 1.6 30 0.0100 0.0160 2209116

1,2,3,4,7,8,9-Hepta CDF pg 2.0 U 2.0 30 0.0100 0.0200 2209116

1,2,3,4,6,7,8,9-Octa CDF pg 3.6 U 3.6 300 0.000300 0.00108 2209116

Total Tetra CDF pg 4.6 J 1.7 30 2209116

Total Penta CDF pg 2.9 J 1.7 30 2209116

Total Hexa CDF pg 1.7 U 1.7 30 2209116

Total Hepta CDF pg 1.8 U 1.8 30 2209116

TOTAL TOXIC EQUIVALENCY pg 6 . 3 0

N/A = Not Applicable

RDL = Reportable Detection Limit

EDL = Estimated Detection Limit

QC Batch = Quality Control Batch

* CDD = Chloro Dibenzo-p-Dioxin, ** CDF = Chloro Dibenzo-p-Furan

TEF = Toxic Equivalency Factor, TEQ = Toxic Equivalency Quotient,

The Total Toxic Equivalency (TEQ) value reported is the sum of Toxic Equivalent Quotients for the congeners tested.

WHO(2005): The 2005 World Health Organization, Human and Mammalian Toxic Equivalency Factors for Dioxins and

Dioxin-like Compounds

( 1 ) EMPC / NDR - Peak detected does not meet ratio criteria and has resulted in an elevated detection limit.

Page 8 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

DIOXINS AND FURANS BY HRMS (STACK SAMPLING TRAIN)

Maxxam ID G K 9 3 7 7

Sampling Date 2010/06/29

18:00

COC Number n/a TOXIC EQUIVALENCY # of

 U n i t s RUN 1-DTE EDL RDL TEF (2005 WHO) TEQ(DL) I s o m e r s QC Batch

MONROE-M23

Surrogate Recovery (%)

C13-1234678 HeptaCDD * % 89 2209116

C13-1234678 HeptaCDF ** % 93 2209116

C13-123478 HexaCDD % 94 2209116

C13-123478 HexaCDF % 99 2209116

C13-1234789 HeptaCDF % 92 2209116

C13-123678 HexaCDD % 100 2209116

C13-123678 HexaCDF % 97 2209116

C13-12378 PentaCDD % 84 2209116

C13-12378 PentaCDF % 86 2209116

C13-123789 HexaCDF % 93 2209116

C13-23478 PentaCDF % 99 2209116

C13-2378 TetraCDD % 86 2209116

C13-2378 TetraCDF % 82 2209116

C13-Octachlorodibenzo-p-Dioxin % 75 2209116

Cl37-2378 TetraCDD % 100 2209116

N/A = Not Applicable

RDL = Reportable Detection Limit

EDL = Estimated Detection Limit

QC Batch = Quality Control Batch

* CDD = Chloro Dibenzo-p-Dioxin, ** CDF = Chloro Dibenzo-p-Furan

TEF = Toxic Equivalency Factor, TEQ = Toxic Equivalency Quotient,

The Total Toxic Equivalency (TEQ) value reported is the sum of Toxic Equivalent Quotients for the congeners tested.

WHO(2005): The 2005 World Health Organization, Human and Mammalian Toxic Equivalency Factors for Dioxins and

Dioxin-like Compounds

Page 9 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

DIOXINS AND FURANS BY HRMS (STACK SAMPLING TRAIN)

Maxxam ID G K 9 3 7 8

Sampling Date 2010/06/30

18:00

COC Number n/a TOXIC EQUIVALENCY # of

 U n i t s RUN 2-DTE EDL RDL TEF (2005 WHO) TEQ(DL) I s o m e r s QC Batch

MONROE-M23

2,3,7,8-Tetra CDD * pg 1.6 U 1.6 30 1.00 1.60 2209116

1,2,3,7,8-Penta CDD pg 2.1 U 2.1 30 1.00 2.10 2209116

1,2,3,4,7,8-Hexa CDD pg 1.8 U 1.8 30 0.100 0.180 2209116

1,2,3,6,7,8-Hexa CDD pg 1.8 U 1.8 30 0.100 0.180 2209116

1,2,3,7,8,9-Hexa CDD pg 1.7 U 1.7 30 0.100 0.170 2209116

1,2,3,4,6,7,8-Hepta CDD pg 2.7 U ( 1 ) 2.7 30 0.0100 0.0270 2209116

1,2,3,4,6,7,8,9-Octa CDD pg 21.2 J 3.8 300 0.000300 0.00636 2209116

Total Tetra CDD pg 3.3 J 1.6 30 2209116

Total Penta CDD pg 19 U ( 1 ) 19 30 2209116

Total Hexa CDD pg 7.2 U ( 1 ) 7.2 30 2209116

Total Hepta CDD pg 3.0 J 1.5 30 2209116

2,3,7,8-Tetra CDF ** pg 8.2 J 1.8 30 0.100 0.820 2209116

1,2,3,7,8-Penta CDF pg 1.6 U 1.6 30 0.0300 0.0480 2209116

2,3,4,7,8-Penta CDF pg 3.6 J 1.5 30 0.300 1.08 2209116

1,2,3,4,7,8-Hexa CDF pg 1.7 U 1.7 30 0.100 0.170 2209116

1,2,3,6,7,8-Hexa CDF pg 1.6 U 1.6 30 0.100 0.160 2209116

2,3,4,6,7,8-Hexa CDF pg 1.8 U 1.8 30 0.100 0.180 2209116

1,2,3,7,8,9-Hexa CDF pg 1.9 U 1.9 30 0.100 0.190 2209116

1,2,3,4,6,7,8-Hepta CDF pg 3.1 U ( 1 ) 3.1 30 0.0100 0.0310 2209116

1,2,3,4,7,8,9-Hepta CDF pg 2.0 U 2.0 30 0.0100 0.0200 2209116

1,2,3,4,6,7,8,9-Octa CDF pg 3.5 U 3.5 300 0.000300 0.00105 2209116

Total Tetra CDF pg 13.3 J 1.8 30 2209116

Total Penta CDF pg 3.6 J 1.5 30 2209116

Total Hexa CDF pg 1.7 U ( 1 ) 1.7 30 2209116

Total Hepta CDF pg 3.4 U ( 1 ) 3.4 30 2209116

TOTAL TOXIC EQUIVALENCY pg 6 . 9 6

N/A = Not Applicable

RDL = Reportable Detection Limit

EDL = Estimated Detection Limit

QC Batch = Quality Control Batch

* CDD = Chloro Dibenzo-p-Dioxin, ** CDF = Chloro Dibenzo-p-Furan

TEF = Toxic Equivalency Factor, TEQ = Toxic Equivalency Quotient,

The Total Toxic Equivalency (TEQ) value reported is the sum of Toxic Equivalent Quotients for the congeners tested.

WHO(2005): The 2005 World Health Organization, Human and Mammalian Toxic Equivalency Factors for Dioxins and

Dioxin-like Compounds

( 1 ) EMPC / NDR - Peak detected does not meet ratio criteria and has resulted in an elevated detection limit.

Page 10 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

DIOXINS AND FURANS BY HRMS (STACK SAMPLING TRAIN)

Maxxam ID G K 9 3 7 8

Sampling Date 2010/06/30

18:00

COC Number n/a TOXIC EQUIVALENCY # of

 U n i t s RUN 2-DTE EDL RDL TEF (2005 WHO) TEQ(DL) I s o m e r s QC Batch

MONROE-M23

Surrogate Recovery (%)

C13-1234678 HeptaCDD * % 94 2209116

C13-1234678 HeptaCDF ** % 95 2209116

C13-123478 HexaCDD % 99 2209116

C13-123478 HexaCDF % 99 2209116

C13-1234789 HeptaCDF % 93 2209116

C13-123678 HexaCDD % 101 2209116

C13-123678 HexaCDF % 97 2209116

C13-12378 PentaCDD % 88 2209116

C13-12378 PentaCDF % 88 2209116

C13-123789 HexaCDF % 93 2209116

C13-23478 PentaCDF % 97 2209116

C13-2378 TetraCDD % 89 2209116

C13-2378 TetraCDF % 86 2209116

C13-Octachlorodibenzo-p-Dioxin % 85 2209116

Cl37-2378 TetraCDD % 99 2209116

N/A = Not Applicable

RDL = Reportable Detection Limit

EDL = Estimated Detection Limit

QC Batch = Quality Control Batch

* CDD = Chloro Dibenzo-p-Dioxin, ** CDF = Chloro Dibenzo-p-Furan

TEF = Toxic Equivalency Factor, TEQ = Toxic Equivalency Quotient,

The Total Toxic Equivalency (TEQ) value reported is the sum of Toxic Equivalent Quotients for the congeners tested.

WHO(2005): The 2005 World Health Organization, Human and Mammalian Toxic Equivalency Factors for Dioxins and

Dioxin-like Compounds

Page 11 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

DIOXINS AND FURANS BY HRMS (STACK SAMPLING TRAIN)

Maxxam ID G K 9 3 7 9

Sampling Date 2010/07/01

18:00

COC Number n/a TOXIC EQUIVALENCY # of

 U n i t s RUN 3-DTE EDL RDL TEF (2005 WHO) TEQ(DL) I s o m e r s QC Batch

MONROE-M23

2,3,7,8-Tetra CDD * pg 1.7 U 1.7 30 1.00 1.70 2209116

1,2,3,7,8-Penta CDD pg 1.9 U 1.9 30 1.00 1.90 2209116

1,2,3,4,7,8-Hexa CDD pg 2.1 U 2.1 30 0.100 0.210 2209116

1,2,3,6,7,8-Hexa CDD pg 2.1 U 2.1 30 0.100 0.210 2209116

1,2,3,7,8,9-Hexa CDD pg 1.9 U 1.9 30 0.100 0.190 2209116

1,2,3,4,6,7,8-Hepta CDD pg 2.9 U ( 1 ) 2.9 30 0.0100 0.0290 2209116

1,2,3,4,6,7,8,9-Octa CDD pg 19.9 J 4.2 300 0.000300 0.00597 2209116

Total Tetra CDD pg 3.0 U ( 2 ) 3.0 30 2209116

Total Penta CDD pg 11.2 J 1.9 30 2209116

Total Hexa CDD pg 9.7 U ( 2 ) 9.7 30 2209116

Total Hepta CDD pg 2.9 U ( 1 ) 2.9 30 2209116

2,3,7,8-Tetra CDF ** pg 4.9 J 2.1 30 0.100 0.490 2209116

1,2,3,7,8-Penta CDF pg 2.0 U 2.0 30 0.0300 0.0600 2209116

2,3,4,7,8-Penta CDF pg 2.3 J 1.9 30 0.300 0.690 2209116

1,2,3,4,7,8-Hexa CDF pg 1.6 U 1.6 30 0.100 0.160 2209116

1,2,3,6,7,8-Hexa CDF pg 1.5 U 1.5 30 0.100 0.150 2209116

2,3,4,6,7,8-Hexa CDF pg 1.7 U 1.7 30 0.100 0.170 2209116

1,2,3,7,8,9-Hexa CDF pg 1.8 U 1.8 30 0.100 0.180 2209116

1,2,3,4,6,7,8-Hepta CDF pg 2.3 U ( 2 ) 2.3 30 0.0100 0.0230 2209116

1,2,3,4,7,8,9-Hepta CDF pg 2.0 U 2.0 30 0.0100 0.0200 2209116

1,2,3,4,6,7,8,9-Octa CDF pg 4.0 U 4.0 300 0.000300 0.00120 2209116

Total Tetra CDF pg 4.9 J 2.1 30 2209116

Total Penta CDF pg 2.3 J 2.0 30 2209116

Total Hexa CDF pg 1.6 U 1.6 30 2209116

Total Hepta CDF pg 2.5 U ( 2 ) 2.5 30 2209116

N/A = Not Applicable

RDL = Reportable Detection Limit

EDL = Estimated Detection Limit

QC Batch = Quality Control Batch

* CDD = Chloro Dibenzo-p-Dioxin, ** CDF = Chloro Dibenzo-p-Furan

TEF = Toxic Equivalency Factor, TEQ = Toxic Equivalency Quotient,

The Total Toxic Equivalency (TEQ) value reported is the sum of Toxic Equivalent Quotients for the congeners tested.

WHO(2005): The 2005 World Health Organization, Human and Mammalian Toxic Equivalency Factors for Dioxins and

Dioxin-like Compounds

( 1 ) RT > 2 seconds - PCDD/DF analysis - Peak detected exceeds expected retention time (from monitoring ion) by

greater than 2 seconds.

( 2 ) EMPC / NDR - Peak detected does not meet ratio criteria and has resulted in an elevated detection limit.

Page 12 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

DIOXINS AND FURANS BY HRMS (STACK SAMPLING TRAIN)

Maxxam ID G K 9 3 7 9

Sampling Date 2010/07/01

18:00

COC Number n/a TOXIC EQUIVALENCY # of

 U n i t s RUN 3-DTE EDL RDL TEF (2005 WHO) TEQ(DL) I s o m e r s QC Batch

MONROE-M23

TOTAL TOXIC EQUIVALENCY pg 6 . 1 9

Surrogate Recovery (%)

C13-1234678 HeptaCDD * % 87 2209116

C13-1234678 HeptaCDF ** % 92 2209116

C13-123478 HexaCDD % 95 2209116

C13-123478 HexaCDF % 96 2209116

C13-1234789 HeptaCDF % 90 2209116

C13-123678 HexaCDD % 98 2209116

C13-123678 HexaCDF % 94 2209116

C13-12378 PentaCDD % 84 2209116

C13-12378 PentaCDF % 85 2209116

C13-123789 HexaCDF % 87 2209116

C13-23478 PentaCDF % 97 2209116

C13-2378 TetraCDD % 81 2209116

C13-2378 TetraCDF % 77 2209116

C13-Octachlorodibenzo-p-Dioxin % 79 2209116

Cl37-2378 TetraCDD % 98 2209116

N/A = Not Applicable

RDL = Reportable Detection Limit

EDL = Estimated Detection Limit

QC Batch = Quality Control Batch

* CDD = Chloro Dibenzo-p-Dioxin, ** CDF = Chloro Dibenzo-p-Furan

TEF = Toxic Equivalency Factor, TEQ = Toxic Equivalency Quotient,

The Total Toxic Equivalency (TEQ) value reported is the sum of Toxic Equivalent Quotients for the congeners tested.

WHO(2005): The 2005 World Health Organization, Human and Mammalian Toxic Equivalency Factors for Dioxins and

Dioxin-like Compounds

Page 13 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

Test Summary

Maxxam ID GK9376 Collected 2010/06/29

Sample ID F.BLANK-DTE MONROE-M23 Shipped

Matrix Stack Sampling Train Received 2010/07/08

Test Description Instrumentation Batch Extracted Analyzed Analyst

Dioxins/Furans in Air (Method 23) HRMS/MS 2209116 2010/07/10 2010/07/20 KKS

PCB Congeners in Air (1668A) HRMS/MSEC 2202679 2010/07/10 2010/07/26 BY

Maxxam ID GK9377 Collected 2010/06/29

Sample ID RUN 1-DTE MONROE-M23 Shipped

Matrix Stack Sampling Train Received 2010/07/08

Test Description Instrumentation Batch Extracted Analyzed Analyst

Dioxins/Furans in Air (Method 23) HRMS/MS 2209116 2010/07/10 2010/07/20 KKS

PCB Congeners in Air (1668A) HRMS/MSEC 2202679 2010/07/10 2010/07/26 BY

Maxxam ID GK9378 Collected 2010/06/30

Sample ID RUN 2-DTE MONROE-M23 Shipped

Matrix Stack Sampling Train Received 2010/07/08

Test Description Instrumentation Batch Extracted Analyzed Analyst

Dioxins/Furans in Air (Method 23) HRMS/MS 2209116 2010/07/10 2010/07/20 KKS

PCB Congeners in Air (1668A) HRMS/MSEC 2202679 2010/07/10 2010/07/26 BY

Maxxam ID GK9379 Collected 2010/07/01

Sample ID RUN 3-DTE MONROE-M23 Shipped

Matrix Stack Sampling Train Received 2010/07/08

Test Description Instrumentation Batch Extracted Analyzed Analyst

Dioxins/Furans in Air (Method 23) HRMS/MS 2209116 2010/07/10 2010/07/20 KKS

PCB Congeners in Air (1668A) HRMS/MSEC 2202679 2010/07/10 2010/07/26 BY

Page 14 of 19
BT Environmental Consulting

Maxxam Job #: B089667

Report Date: 2010/07/28 Project name: DTE MONROE ICR TESTING

GENERAL COMMENTS

Results relate only to the items tested.

Page 15 of 19
BT Environmental Consulting

Attention: Tom Snyder 

Client Project #:

P.O. #:

Project name: DTE MONROE ICR TESTING

Quality Assurance Report

Maxxam Job Number: GB089667

QA/QC Date

Batch Analyzed

Num Init QC Type Parameter yyyy/mm/dd Value %Recovery Units QC Limits

2202679 BY Spiked Blank C13-233'44'55'-HeptaCB-(189) 2010/07/17 136 % 20 - 150

Spiked Blank DUP C13-233'44'55'-HeptaCB-(189) 2010/07/17 125 % 20 - 150

Spiked Blank C13-233'44'5-HexaCB-(156) 2010/07/17 121 % 20 - 150

Spiked Blank DUP C13-233'44'5-HexaCB-(156) 2010/07/17 111 % 20 - 150

Spiked Blank C13-233'44'5'-HexaCB-(157) 2010/07/17 121 % 20 - 150

Spiked Blank DUP C13-233'44'5'-HexaCB-(157) 2010/07/17 111 % 20 - 150

Spiked Blank C13-233'44'-PentaCB-(105) 2010/07/17 131 % 20 - 150

Spiked Blank DUP C13-233'44'-PentaCB-(105) 2010/07/17 120 % 20 - 150

Spiked Blank C13-23'44'55'-HexaCB-(167) 2010/07/17 122 % 20 - 150

Spiked Blank DUP C13-23'44'55'-HexaCB-(167) 2010/07/17 113 % 20 - 150

Spiked Blank C13-2344'5-PentaCB-(114) 2010/07/17 126 % 20 - 150

Spiked Blank DUP C13-2344'5-PentaCB-(114) 2010/07/17 113 % 20 - 150

Spiked Blank C13-23'44'5-PentaCB-(118) 2010/07/17 129 % 20 - 150

Spiked Blank DUP C13-23'44'5-PentaCB-(118) 2010/07/17 119 % 20 - 150

Spiked Blank C13-2'344'5-PentaCB-(123) 2010/07/17 129 % 20 - 150

Spiked Blank DUP C13-2'344'5-PentaCB-(123) 2010/07/17 117 % 20 - 150

Spiked Blank C13-33'44'55'-HexaCB-(169) 2010/07/17 125 % 20 - 150

Spiked Blank DUP C13-33'44'55'-HexaCB-(169) 2010/07/17 116 % 20 - 150

Spiked Blank C13-33'44'5-PentaCB-(126) 2010/07/17 136 % 20 - 150

Spiked Blank DUP C13-33'44'5-PentaCB-(126) 2010/07/17 128 % 20 - 150

Spiked Blank C13-33'44'-TetraCB-(77) 2010/07/17 119 % 20 - 150

Spiked Blank DUP C13-33'44'-TetraCB-(77) 2010/07/17 109 % 20 - 150

Spiked Blank C13-344'5-TetraCB-(81) 2010/07/17 118 % 20 - 150

Spiked Blank DUP C13-344'5-TetraCB-(81) 2010/07/17 107 % 20 - 150

Spiked Blank 33'44'-TetraCB-(77) 2010/07/17 111 % N/A

Spiked Blank DUP 33'44'-TetraCB-(77) 2010/07/17 112 % N/A

RPD 33'44'-TetraCB-(77) 2010/07/17 0.9 % 20

Spiked Blank 344'5-TetraCB-(81) 2010/07/17 111 % N/A

Spiked Blank DUP 344'5-TetraCB-(81) 2010/07/17 111 % N/A

RPD 344'5-TetraCB-(81) 2010/07/17 0 % 20

Spiked Blank 233'44'-PentaCB-(105) 2010/07/17 105 % N/A

Spiked Blank DUP 233'44'-PentaCB-(105) 2010/07/17 108 % N/A

RPD 233'44'-PentaCB-(105) 2010/07/17 2.8 % 20

Spiked Blank 2344'5-PentaCB-(114) 2010/07/17 107 % N/A

Spiked Blank DUP 2344'5-PentaCB-(114) 2010/07/17 110 % N/A

RPD 2344'5-PentaCB-(114) 2010/07/17 2.8 % 20

Spiked Blank 23'44'5-PentaCB-(118) 2010/07/17 105 % N/A

Spiked Blank DUP 23'44'5-PentaCB-(118) 2010/07/17 106 % N/A

RPD 23'44'5-PentaCB-(118) 2010/07/17 0.9 % 20

Spiked Blank 23'44'5'-PentaCB-(123) 2010/07/17 108 % N/A

Spiked Blank DUP 23'44'5'-PentaCB-(123) 2010/07/17 109 % N/A

RPD 23'44'5'-PentaCB-(123) 2010/07/17 0.9 % 20

Spiked Blank 33'44'5-PentaCB-(126) 2010/07/17 109 % N/A

Spiked Blank DUP 33'44'5-PentaCB-(126) 2010/07/17 109 % N/A

RPD 33'44'5-PentaCB-(126) 2010/07/17 0 % 20

Spiked Blank HexaCB-(156)+(157) 2010/07/17 107 % N/A

Spiked Blank DUP HexaCB-(156)+(157) 2010/07/17 108 % N/A

RPD HexaCB-(156)+(157) 2010/07/17 0.9 % 20

Spiked Blank 23'44'55'-HexaCB-(167) 2010/07/17 105 % N/A

Spiked Blank DUP 23'44'55'-HexaCB-(167) 2010/07/17 106 % N/A

RPD 23'44'55'-HexaCB-(167) 2010/07/17 0.9 % 20

Spiked Blank 33'44'55'-HexaCB-(169) 2010/07/17 107 % N/A

Spiked Blank DUP 33'44'55'-HexaCB-(169) 2010/07/17 107 % N/A

RPD 33'44'55'-HexaCB-(169) 2010/07/17 0 % 20

Spiked Blank 233'44'55'-HeptaCB-(189) 2010/07/17 102 % N/A

Maxxam Analytics International Corporation o/a Maxxam Analytics Burlington:5555 North Service Road, Burlington, Ontario L7L 5H7 Telephone(905) 332-8788 Fax(905) 332-9169

Page 16 of 19
BT Environmental Consulting

Attention: Tom Snyder 

Client Project #:

P.O. #:

Project name: DTE MONROE ICR TESTING

Quality Assurance Report (Continued)

Maxxam Job Number: GB089667

QA/QC Date

Batch Analyzed

Num Init QC Type Parameter yyyy/mm/dd Value %Recovery Units QC Limits

2202679 BY Spiked Blank DUP 233'44'55'-HeptaCB-(189) 2010/07/17 102 % N/A

RPD 233'44'55'-HeptaCB-(189) 2010/07/17 0 % N/A

Method Blank C13-233'44'55'-HeptaCB-(189) 2010/07/17 122 % 20 - 150

C13-233'44'5-HexaCB-(156) 2010/07/17 109 % 20 - 150

C13-233'44'5'-HexaCB-(157) 2010/07/17 109 % 20 - 150

C13-233'44'-PentaCB-(105) 2010/07/17 132 % 20 - 150

C13-23'44'55'-HexaCB-(167) 2010/07/17 111 % 20 - 150

C13-2344'5-PentaCB-(114) 2010/07/17 125 % 20 - 150

C13-23'44'5-PentaCB-(118) 2010/07/17 130 % 20 - 150

C13-2'344'5-PentaCB-(123) 2010/07/17 127 % 20 - 150

C13-33'44'55'-HexaCB-(169) 2010/07/17 110 % 20 - 150

C13-33'44'5-PentaCB-(126) 2010/07/17 129 % 20 - 150

C13-33'44'-TetraCB-(77) 2010/07/17 126 % 20 - 150

C13-344'5-TetraCB-(81) 2010/07/17 121 % 20 - 150

33'44'-TetraCB-(77) 2010/07/17 0.0022 U, EDL=0.0022 ( 1 ) ng

344'5-TetraCB-(81) 2010/07/17 0.0016 U, EDL=0.0016 ng

233'44'-PentaCB-(105) 2010/07/17 0.0049 J, EDL=0.0026 ng

2344'5-PentaCB-(114) 2010/07/17 0.0026 U, EDL=0.0026 ng

23'44'5-PentaCB-(118) 2010/07/17 0.012 U, EDL=0.012 ( 1 ) ng

23'44'5'-PentaCB-(123) 2010/07/17 0.0026 U, EDL=0.0026 ng

33'44'5-PentaCB-(126) 2010/07/17 0.0026 U, EDL=0.0026 ng

HexaCB-(156)+(157) 2010/07/17 0.0049 U, EDL=0.0049 ( 1 ) ng

23'44'55'-HexaCB-(167) 2010/07/17 0.0027 U, EDL=0.0027 ( 1 ) ng

33'44'55'-HexaCB-(169) 2010/07/17 0.0013 U, EDL=0.0013 ( 1 ) ng

233'44'55'-HeptaCB-(189) 2010/07/17 0.0022 U, EDL=0.0022 ng

2209116 KKS Spiked Blank C13-1234678 HeptaCDD 2010/07/17 102 % 25 - 130

Spiked Blank DUP C13-1234678 HeptaCDD 2010/07/17 102 % 25 - 130

Spiked Blank C13-1234678 HeptaCDF 2010/07/17 100 % 25 - 130

Spiked Blank DUP C13-1234678 HeptaCDF 2010/07/17 98 % 25 - 130

Spiked Blank C13-123678 HexaCDD 2010/07/17 92 % 40 - 130

Spiked Blank DUP C13-123678 HexaCDD 2010/07/17 91 % 40 - 130

Spiked Blank C13-123678 HexaCDF 2010/07/17 87 % 40 - 130

Spiked Blank DUP C13-123678 HexaCDF 2010/07/17 82 % 40 - 130

Spiked Blank C13-12378 PentaCDD 2010/07/17 79 % 40 - 130

Spiked Blank DUP C13-12378 PentaCDD 2010/07/17 73 % 40 - 130

Spiked Blank C13-12378 PentaCDF 2010/07/17 73 % 40 - 130

Spiked Blank DUP C13-12378 PentaCDF 2010/07/17 65 % 40 - 130

Spiked Blank C13-123789 HexaCDF 2010/07/17 84 % 40 - 130

Spiked Blank DUP C13-123789 HexaCDF 2010/07/17 80 % 40 - 130

Spiked Blank C13-2378 TetraCDD 2010/07/17 55 % 40 - 130

Spiked Blank DUP C13-2378 TetraCDD 2010/07/17 45 % 40 - 130

Spiked Blank C13-2378 TetraCDF 2010/07/17 55 % 40 - 130

Spiked Blank DUP C13-2378 TetraCDF 2010/07/17 42 % 40 - 130

Spiked Blank C13-Octachlorodibenzo-p-Dioxin 2010/07/17 100 % 25 - 130

Spiked Blank DUP C13-Octachlorodibenzo-p-Dioxin 2010/07/17 101 % 25 - 130

Spiked Blank 2,3,7,8-Tetra CDD 2010/07/17 105 % 80 - 140

Spiked Blank DUP 2,3,7,8-Tetra CDD 2010/07/17 108 % 80 - 140

RPD 2,3,7,8-Tetra CDD 2010/07/17 NC % 20

Spiked Blank 1,2,3,7,8-Penta CDD 2010/07/17 108 % 80 - 140

Spiked Blank DUP 1,2,3,7,8-Penta CDD 2010/07/17 109 % 80 - 140

RPD 1,2,3,7,8-Penta CDD 2010/07/17 NC % 20

Spiked Blank 1,2,3,4,7,8-Hexa CDD 2010/07/17 106 % 80 - 140

Spiked Blank DUP 1,2,3,4,7,8-Hexa CDD 2010/07/17 106 % 80 - 140

RPD 1,2,3,4,7,8-Hexa CDD 2010/07/17 NC % 20

Spiked Blank 1,2,3,6,7,8-Hexa CDD 2010/07/17 102 % 80 - 140

Maxxam Analytics International Corporation o/a Maxxam Analytics Burlington:5555 North Service Road, Burlington, Ontario L7L 5H7 Telephone(905) 332-8788 Fax(905) 332-9169

Page 17 of 19
BT Environmental Consulting

Attention: Tom Snyder 

Client Project #:

P.O. #:

Project name: DTE MONROE ICR TESTING

Quality Assurance Report (Continued)

Maxxam Job Number: GB089667

QA/QC Date

Batch Analyzed

Num Init QC Type Parameter yyyy/mm/dd Value %Recovery Units QC Limits

2209116 KKS Spiked Blank DUP 1,2,3,6,7,8-Hexa CDD 2010/07/17 101 % 80 - 140

RPD 1,2,3,6,7,8-Hexa CDD 2010/07/17 NC % 20

Spiked Blank 1,2,3,7,8,9-Hexa CDD 2010/07/17 105 % 80 - 140

Spiked Blank DUP 1,2,3,7,8,9-Hexa CDD 2010/07/17 108 % 80 - 140

RPD 1,2,3,7,8,9-Hexa CDD 2010/07/17 NC % 20

Spiked Blank 1,2,3,4,6,7,8-Hepta CDD 2010/07/17 86 % 80 - 140

Spiked Blank DUP 1,2,3,4,6,7,8-Hepta CDD 2010/07/17 87 % 80 - 140

RPD 1,2,3,4,6,7,8-Hepta CDD 2010/07/17 NC % 20

Spiked Blank 1,2,3,4,6,7,8,9-Octa CDD 2010/07/17 101 % 80 - 140

Spiked Blank DUP 1,2,3,4,6,7,8,9-Octa CDD 2010/07/17 103 % 80 - 140

RPD 1,2,3,4,6,7,8,9-Octa CDD 2010/07/17 NC % 20

Spiked Blank 2,3,7,8-Tetra CDF 2010/07/17 103 % 80 - 140

Spiked Blank DUP 2,3,7,8-Tetra CDF 2010/07/17 107 % 80 - 140

RPD 2,3,7,8-Tetra CDF 2010/07/17 NC % 20

Spiked Blank 1,2,3,7,8-Penta CDF 2010/07/17 107 % 80 - 140

Spiked Blank DUP 1,2,3,7,8-Penta CDF 2010/07/17 105 % 80 - 140

RPD 1,2,3,7,8-Penta CDF 2010/07/17 NC % 20

Spiked Blank 2,3,4,7,8-Penta CDF 2010/07/17 115 % 80 - 140

Spiked Blank DUP 2,3,4,7,8-Penta CDF 2010/07/17 113 % 80 - 140

RPD 2,3,4,7,8-Penta CDF 2010/07/17 NC % 20

Spiked Blank 1,2,3,4,7,8-Hexa CDF 2010/07/17 105 % 80 - 140

Spiked Blank DUP 1,2,3,4,7,8-Hexa CDF 2010/07/17 107 % 80 - 140

RPD 1,2,3,4,7,8-Hexa CDF 2010/07/17 NC % 20

Spiked Blank 1,2,3,6,7,8-Hexa CDF 2010/07/17 105 % 80 - 140

Spiked Blank DUP 1,2,3,6,7,8-Hexa CDF 2010/07/17 108 % 80 - 140

RPD 1,2,3,6,7,8-Hexa CDF 2010/07/17 NC % 20

Spiked Blank 2,3,4,6,7,8-Hexa CDF 2010/07/17 113 % 80 - 140

Spiked Blank DUP 2,3,4,6,7,8-Hexa CDF 2010/07/17 116 % 80 - 140

RPD 2,3,4,6,7,8-Hexa CDF 2010/07/17 NC % 20

Spiked Blank 1,2,3,7,8,9-Hexa CDF 2010/07/17 109 % 80 - 140

Spiked Blank DUP 1,2,3,7,8,9-Hexa CDF 2010/07/17 112 % 80 - 140

RPD 1,2,3,7,8,9-Hexa CDF 2010/07/17 NC % 20

Spiked Blank 1,2,3,4,6,7,8-Hepta CDF 2010/07/17 95 % 80 - 140

Spiked Blank DUP 1,2,3,4,6,7,8-Hepta CDF 2010/07/17 99 % 80 - 140

RPD 1,2,3,4,6,7,8-Hepta CDF 2010/07/17 NC % 20

Spiked Blank 1,2,3,4,7,8,9-Hepta CDF 2010/07/17 94 % 80 - 140

Spiked Blank DUP 1,2,3,4,7,8,9-Hepta CDF 2010/07/17 97 % 80 - 140

RPD 1,2,3,4,7,8,9-Hepta CDF 2010/07/17 NC % 20

Spiked Blank 1,2,3,4,6,7,8,9-Octa CDF 2010/07/17 96 % 80 - 140

Spiked Blank DUP 1,2,3,4,6,7,8,9-Octa CDF 2010/07/17 97 % 80 - 140

RPD 1,2,3,4,6,7,8,9-Octa CDF 2010/07/17 NC % 20

Method Blank C13-1234678 HeptaCDD 2010/07/18 101 % 25 - 130

C13-1234678 HeptaCDF 2010/07/18 98 % 25 - 130

C13-123678 HexaCDD 2010/07/18 92 % 40 - 130

C13-123678 HexaCDF 2010/07/18 85 % 40 - 130

C13-12378 PentaCDD 2010/07/18 84 % 40 - 130

C13-12378 PentaCDF 2010/07/18 81 % 40 - 130

C13-123789 HexaCDF 2010/07/18 84 % 40 - 130

C13-2378 TetraCDD 2010/07/18 69 % 40 - 130

C13-2378 TetraCDF 2010/07/18 69 % 40 - 130

C13-Octachlorodibenzo-p-Dioxin 2010/07/18 100 % 25 - 130

2,3,7,8-Tetra CDD 2010/07/18 1.8 U, EDL=1.8 pg

1,2,3,7,8-Penta CDD 2010/07/18 1.6 U, EDL=1.6 pg

1,2,3,4,7,8-Hexa CDD 2010/07/18 1.7 U, EDL=1.7 pg

1,2,3,6,7,8-Hexa CDD 2010/07/18 1.7 U, EDL=1.7 pg

Maxxam Analytics International Corporation o/a Maxxam Analytics Burlington:5555 North Service Road, Burlington, Ontario L7L 5H7 Telephone(905) 332-8788 Fax(905) 332-9169

Page 18 of 19
BT Environmental Consulting

Attention: Tom Snyder 

Client Project #:

P.O. #:

Project name: DTE MONROE ICR TESTING

Quality Assurance Report (Continued)

Maxxam Job Number: GB089667

QA/QC Date

Batch Analyzed

Num Init QC Type Parameter yyyy/mm/dd Value %Recovery Units QC Limits

2209116 KKS Method Blank 1,2,3,7,8,9-Hexa CDD 2010/07/18 1.5 U, EDL=1.5 pg

1,2,3,4,6,7,8-Hepta CDD 2010/07/18 7.2 J, EDL=1.8 pg

1,2,3,4,6,7,8,9-Octa CDD 2010/07/18 50.8 J, EDL=3.8 pg

Total Tetra CDD 2010/07/18 3.7 U, EDL=3.7 ( 1 ) pg

Total Penta CDD 2010/07/18 3.1 U, EDL=3.1 ( 1 ) pg

Total Hexa CDD 2010/07/18 8.1 U, EDL=8.1 ( 1 ) pg

Total Hepta CDD 2010/07/18 11.6 J, EDL=1.8 pg

2,3,7,8-Tetra CDF 2010/07/18 1.7 U, EDL=1.7 pg

1,2,3,7,8-Penta CDF 2010/07/18 1.9 U, EDL=1.9 pg

2,3,4,7,8-Penta CDF 2010/07/18 1.8 U, EDL=1.8 pg

1,2,3,4,7,8-Hexa CDF 2010/07/18 1.6 U, EDL=1.6 pg

1,2,3,6,7,8-Hexa CDF 2010/07/18 1.5 U, EDL=1.5 pg

2,3,4,6,7,8-Hexa CDF 2010/07/18 1.7 U, EDL=1.7 pg

1,2,3,7,8,9-Hexa CDF 2010/07/18 1.8 U, EDL=1.8 pg

1,2,3,4,6,7,8-Hepta CDF 2010/07/18 1.4 U, EDL=1.4 pg

1,2,3,4,7,8,9-Hepta CDF 2010/07/18 1.7 U, EDL=1.7 pg

1,2,3,4,6,7,8,9-Octa CDF 2010/07/18 3.1 U, EDL=3.1 pg

Total Tetra CDF 2010/07/18 1.7 U, EDL=1.7 pg

Total Penta CDF 2010/07/18 1.9 U, EDL=1.9 pg

Total Hexa CDF 2010/07/18 1.6 U, EDL=1.6 pg

Total Hepta CDF 2010/07/18 1.5 U, EDL=1.5 pg

Duplicate: Paired analysis of a separate portion of the same sample. Used to evaluate the variance in the measurement.

Spiked Blank: A blank matrix to which a known amount of the analyte has been added. Used to evaluate analyte recovery.

Method Blank: A blank matrix containing all reagents used in the analytical procedure. Used to identify laboratory contamination.

Surrogate: A pure or isotopically labeled compound whose behavior mirrors the analytes of interest. Used to evaluate extraction efficiency.

NC (RPD): The RPD was not calculated. The level of analyte detected in the parent sample and its duplicate was not sufficiently significant to permit a

reliable calculation.

( 1 ) EMPC / NDR - Peak detected does not meet ratio criteria and has resulted in an elevated detection limit.

Maxxam Analytics International Corporation o/a Maxxam Analytics Burlington:5555 North Service Road, Burlington, Ontario L7L 5H7 Telephone(905) 332-8788 Fax(905) 332-9169

Page 19 of 19



Appendix E 

Example Calculations 
EXAMPLE CALCULATIONS

Method 1-4

Moisture Content

wc VKV 11 ⋅=

wsg VKV 22 ⋅=

Where: Vwc = volume of water vapor condensed in impingers at standard conditions (ft3

) 

 K1 = 0.04715 ft3

/g water 

 V1 = mass of water collected in impingers (g) 

Vwsg = volume of water vapor collected in silica gel at standard conditions (ft3

) 

K2 = 0.04715 ft3/g water 

V2 = mass of water collected by silica gel (g) 

Gas Volume Standardization

⎟

⎟

⎟

⎟

⎠

⎞

⎜

⎜

⎜

⎜

⎝

⎛ Δ

+

⎟

⎟

⎠

⎞

⎜

⎜

⎝

⎛ =

m

b

std

std

mmstd T

H P

P

T YVV 6.13

Where: Vstd = volume of gas sampled at standard conditions 

Vm = volume of gas measured by dry gas meter (ft3

) 

 Ym = dry gas meter correction factor (dimensionless) 

 Tstd = standard temperature (o

R = 460 + oF) 

 Pstd = standard pressure (“Hg) 

 Pb = barometric pressure (“Hg) 

 ΔH = average orifice differential pressure (“H2O) 

 Tm = average meter temperature (o

R) 

Moisture Fraction

wc wsg std

wc wsg

ws VVV

VV

B

++

+ =

Where: Bws = exhaust gas moisture content 
Absolute Stack Gas Temperature, Ts (o

R)

s s 460 += tT

Where: ts = Measured stack gas temperature (o

F) 

Absolute Stack Gas Pressure, Ps (in. Hg)

⎟

⎠

⎞ ⎜

⎝

⎛ +=

6.13

stat

bars

P

PP

Where: Pbar = Barometric pressure at test site (in. Hg) 

 Pstat = Stack static pressure (in. Hg) 

Stack Gas Molecular Weight, Dry Basis (lb/lb mole)

M d = CO2 + O2 + 2 + CON )%(%28.0)(%32.0)(%44.0

Stack Gas Molecular Weight, Wet Basis (lb/lb mole)

⎟

⎠

⎞ ⎜

⎝

⎛ ⎟ +

⎠

⎞ ⎜

⎝

⎛ −= 100

18

100

1 ws ws

ds

BB MM

Stack Gas Velocity, Vs (fpm)

ss

s

s pp MP

T V ⎟ ΔPCK⎠

⎞ ⎜

⎝

⎛ = min

sec 60

Where: Kp = Pitot tube constant equal to 85.49 

).)((

).)(/(

sec 2OHinR

Hginmolelblbft

o

⋅

Cp = Pitot tube coefficient, dimensionless 

ΔP = The average square root of the velocity head of stack gas (in. H2O) 

Ms = Molecular weight of the stack gas, wet basis (lb/lb mole) 

Average Stack Gas Volumetric Flowrate, Qs (cfm)

ss ⋅= AVQ

Where: Vs = Stack gas velocity (fpm) 
A = Cross-sectional area of stack (ft2

) 

Standard Stack Gas Volumetric Flowrate, Qstd (scfm)

⎟

⎟

⎠

⎞

⎜

⎜

⎝

⎛

⎟

⎟

⎠

⎞

⎜

⎜

⎝

⎛ = Hgin

P

T

R QQ s

s

o

sstd .92.29

530

Where: Ts = Absolute stack gas temperature (o

R) 

Ps = Absolute stack gas pressure (in. Hg) 

Dry Standard Stack Gas Volumetric Flowrate, Qstd,dry (dscfm)

( ) ,drystd std 1−= BQQ ws

Method 23

Concentration, C1 (lb/ft3, dry basis)

Vt

m C

000,000,600,453 1 =

Where: m = mass of pollutant (ng). 

Vt = total volume of gas sampled (ft3

). 

 453,600,000,000 = conversion factor, nanograms to pounds. 

Mass Emission Rate (lb/hr)

⎟

⎠

⎞ ⎜

⎝

⎛ = hr QC drystd

min Emission Rate ,1 60

Mass Loading (lb/1000 lb, dry)

MWd

mollb

ft C

Loading

⎟

⎟

⎠

⎞

⎜

⎜

⎝

⎛

⋅ ⋅=

3

1 9.386

1000
Method 7E 

Analyzer Drift Correction

( ) ⎟

⎟

⎠

⎞

⎜

⎜

⎝

⎛

− −=

om

ma

o CC

C CCC

Where: C = Effluent gas concentration, dry basis (ppm or %). 

C = Average gas concentration indicated by gas analyzer, dry basis (ppm 

or %). 

= Average of initial and final system calibration bias check responses 

for the zero gas (ppm or %). 

Co

 = Actual concentration of the upscale calibration gas (ppm or %). Cma

= Average of initial and final system calibration bias check responses 

for the upscale calibration gas (ppm or %). 

Cm

Mass Flowrate (lb/hr)

⎟

⎠

⎞ ⎜

⎝

⎛

⎟

⎟

⎠

⎞

⎜

⎜

⎝

⎛

⎟

⎟

⎠

⎞

⎜

⎜

⎝

⎛

⎟

⎟

⎠

⎞

⎜

⎜

⎝

⎛ = ft hr

m

g

lb

mg

g CQM drystd

min 60

31.35

1

6.453

1

000,1

1

3

3

,

Where: C = Pollutant concentration (mg/dscm) 

 MW = molecular weight lb/lb mol 

Emission Rate as lb/mmbtu

⎟

⎠

⎞ ⎜

⎝

⎛ = hrmmbt

M

M hrlb

mmbtulb /

/

/

Where: Mlb/hr = Pollutant Emission Rate (lb/hr) 

 Mmbtu/hr = million BTUs per hour 
ng/dscm

⎟

⎟

⎠

⎞

⎜

⎜

⎝

⎛ = Vmstd

CC 31.35

2

Where: C = Pollutant Catch (ng) 

 35.31 = Ft^3 per m^3 

 Vmstd = Sample volume corrected to standard conditions (ft^3) 

 

Correction to 7% O2

⎟

⎟

⎠

⎞

⎜

⎜

⎝

⎛

−

− =

2

2

2%7 %9.20

%79.20

O

O

O MM

Where: M = Pollutant Emission Rate or Concentration 

 %O2 = Measured %O2 value for run 
Appendix F 

Production Data