### Name:

Title: Company: Sign Date: Name: Title: Company: Sign Date: Permitted Facility Representative / Date Testing Company Representative / Date 

## Minnkota Power Cooperative Inc.

Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Sunday, January 30, 2011 Page 1 of 12

### Minnkota Power Cooperative Inc.

Facility Information: Milton R. Young Station
3401 24th Street SW

Center ND58530-9507 Contact:Kevin Thomas Phone:701-220-8819 Fax: Email:kthomas@minnkota.com Testing Company: GE International, Inc. 1301 Corporate Center Drive

Eagan MN55121 Contact:David Wainio Phone:651-6860700 Ex 12 Fax: 651-686-4434 Email:david.wainio@ge.com

Air Permit Number: T5-F76009 Permitted Source ID/Name: Milton R. Young Station Permitted Maximum Process Rate: 3200 x 1E+6 BTU/hr Max. Normal Operation Process Rate: 2700 x 1E+6 BTU/hr Target Process Test Rate 2500 x 1E+6 BTU/hr

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Industry/SCC/NAIS221112

Sampling Location Information:

Test Parameter Information: AFS #:3806500020 FRS #:110000428387

SCC / Description10100303 External Combustion Boilers - Electric Generation - Lignite - Cyclone Furnace

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width Unit 1 228 0 0 4 6 0 0

Target Parameter Test Method Number of

Test RunsTest Run

DurationSample

Points Comments Location2,3,7,8-TCDD Method 23 3 482 0 Unit 1 1,2,3,7,8-PeCDD Method 23 3 482 0 Unit 1 1,2,3,4,7,8-HxCDD Method 23 3 482 0 Unit 1 1,2,3,6,7,8-HxCDD Method 23 3 482 0 Unit 1 1,2,3,7,8,9-HxCDD Method 23 3 482 0 Unit 1 1,2,3,4,6,7,8-HpCDD Method 23 3 482 0 Unit 1 OCDD Method 23 3 482 0 Unit 1



### Sunday, January 30, 2011 Page 2 of 12

### Minnkota Power Cooperative Inc.

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.

2,3,7,8-TCDF Method 23 3 482 0 Unit 1 1,2,3,7,8-PeCDF Method 23 3 482 0 Unit 1 2,3,4,7,8-PeCDF Method 23 3 482 0 Unit 1 1,2,3,4,7,8-HxCDF Method 23 3 482 0 Unit 1 1,2,3,6,7,8-HxCDF Method 23 3 482 0 Unit 1 2,3,4,6,7,8-HxCDF Method 23 3 482 0 Unit 1 1,2,3,7,8,9-HxCDF Method 23 3 482 0 Unit 1 1,2,3,4,6,7,8-HpCDF Method 23 3 482 0 Unit 1 1,2,3,4,7,8,9-HpCDF Method 23 3 482 0 Unit 1 OCDF Method 23 3 482 0 Unit 1 Other TCDD Method 23 3 482 0 Unit 1 Other PeCDD Method 23 3 482 0 Unit 1 Other HxCDD Method 23 3 482 0 Unit 1 Other HpCDD Method 23 3 482 0 Unit 1 Other TCDF Method 23 3 482 0 Unit 1 Other PeCDF Method 23 3 482 0 Unit 1 Other HxCDF Method 23 3 482 0 Unit 1 Other HpCDF Method 23 3 482 0 Unit 1 3,3',4,4'-TCB (PCB77) Method 23 3 482 0 Unit 1 3,4,4',5-TCB (PCB81) Method 23 3 482 0 Unit 1 2,3,4,4',5-PeCB (PCB114) Method 23 3 482 0 Unit 1 2,3',4,4',5-PeCB (PCB118) Method 23 3 482 0 Unit 1 2',3,4,4',5-PeCB (PCB123) Method 23 3 482 0 Unit 1 3,3',4,4',5-PeCB (PCB126) Method 23 3 482 0 Unit 1 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 482 0 Unit 1

2,3',4,4',5,5'-HxCB (PCB167)Method 23 3 482 0 Unit 1 3,3',4,4',5,5'-HxCB (PCB169)Method 23 3 482 0 Unit 1 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 482 0 Unit 1

Co2 Method 3A CO2 3 482 0 Unit 1 O2 Method 3A O2 3 482 0 Unit 1



### Sunday, January 30, 2011 Page 3 of 12

### Minnkota Power Cooperative Inc.

Sampling / Stack Data Results Summary



### LocationUnit 1 - Method 23 Average Run Number 1 2 3
Test Date 5/18/20105/19/2010 5/20/2010 Run Start Time 8:05:00 AM 7:30:00 AM6:56:00 AM

Run Finish Time 5:01:30 PM3:54:00 PM3:22:00 PM Net Run Time, minutes 486 480 480 Dry Gas Meter Volume Sampled, dscf 283.583 281.748 291.204 285.512 Moisture Content of Stack Gas, % 15.16 15.23 15.17 15.187 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 14.4 14.6 14.5 14.500 Oxygen, % 5.5 5.5 5.6 5.533 Average Stack Gas Temperature, °F 333.22 337.92 334.15 335.097 Dry Volumetric Flow Rate, dry scfm 623,214.4648,019.9 660,597.9643,944.067 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,197,626.51,250,533.01,267,885.01,238,681.50 0 Percent Isokinetic of Sampling Rate, % 100.6 97.3 98.6 98.833 F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000
Fw 11950 11950 11950 11,950.000
Fc 1910 1910 1910 1,910.000



### Sunday, January 30, 2011 Page 4 of 12

### Minnkota Power Cooperative Inc.

Emissions Summary



### Location:Unit 1 - Method 23 Compound:1,2,3,4,6,7,8-HpCDD Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:1,2,3,4,6,7,8-HpCDF Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:1,2,3,4,7,8,9-HpCDF Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:1,2,3,4,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:1,2,3,4,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:1,2,3,6,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:1,2,3,6,7,8-HxCDF Average



### Sunday, January 30, 2011 Page 5 of 12

### Minnkota Power Cooperative Inc.

RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:1,2,3,7,8,9-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:1,2,3,7,8,9-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:1,2,3,7,8-PeCDD Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:1,2,3,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber 1 2 3 Mass_mg 0.0000005 0.0000005 0.0000005 0.000 lb/mmBtuO2 5.20E-11 5.24E-11 5.10E-11 0.000 ng/dscm 6.23E-02 6.27E-02 6.06E-02 0.062 ng/dscm@7%O2 5.62E-02 5.66E-02 5.51E-02 0.056 

### Compound:2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber 1 2 3 Mass_mg 0.0000005 0.0000005 0.0000005 0.000 lb/mmBtuO2 5.20E-11 5.24E-11 5.10E-11 0.000 ng/dscm 6.23E-02 6.27E-02 6.06E-02 0.062 ng/dscm@7%O2 5.62E-02 5.66E-02 5.51E-02 0.056



### Sunday, January 30, 2011 Page 6 of 12

### Minnkota Power Cooperative Inc.

Compound:2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber 1 2 3 Mass_mg 0.0000005 0.0000005 0.0000005 0.000 lb/mmBtuO2 5.20E-11 5.24E-11 5.10E-11 0.000 ng/dscm 6.23E-02 6.27E-02 6.06E-02 0.062 ng/dscm@7%O2 5.62E-02 5.66E-02 5.51E-02 0.056 

### Compound:2,3,4,4',5-PeCB (PCB114) Average RunNumber 1 2 3 Mass_mg 0.0000005 0.0000005 0.0000005 0.000 lb/mmBtuO2 5.20E-11 5.24E-11 5.10E-11 0.000 ng/dscm 6.23E-02 6.27E-02 6.06E-02 0.062 ng/dscm@7%O2 5.62E-02 5.66E-02 5.51E-02 0.056 

### Compound:2,3',4,4',5-PeCB (PCB118) Average RunNumber 1 2 3 Mass_mg 0.000000964 0.000000844 0.000000853 0.000 lb/mmBtuO2 1.00E-10 8.84E-11 8.70E-11 0.000 ng/dscm 1.20E-01 1.06E-01 1.03E-01 0.110 ng/dscm@7%O2 1.08E-01 9.57E-02 9.36E-02 0.099 

### Compound:2',3,4,4',5-PeCB (PCB123) Average RunNumber 1 2 3 Mass_mg 0.0000005 0.0000005 0.0000005 0.000 lb/mmBtuO2 5.20E-11 5.24E-11 5.10E-11 0.000 ng/dscm 6.23E-02 6.27E-02 6.06E-02 0.062 ng/dscm@7%O2 5.62E-02 5.66E-02 5.51E-02 0.056 

### Compound:2,3,4,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:2,3,4,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:2,3,7,8-TCDD Average RunNumber 1 2 3 Mass_mg 0.00000002 0.00000002 0.00000002 0.000 lb/mmBtuO2 2.08E-12 2.09E-12 2.04E-12 0.000



### Sunday, January 30, 2011 Page 7 of 12

### Minnkota Power Cooperative Inc.

ng/dscm 2.49E-03 2.51E-03 2.43E-03 0.002 ng/dscm@7%O2 2.25E-03 2.27E-03 2.21E-03 0.002 

### Compound:2,3,7,8-TCDF Average RunNumber 1 2 3 Mass_mg 0.00000002 0.00000002 0.00000002 0.000 lb/mmBtuO2 2.08E-12 2.09E-12 2.04E-12 0.000 ng/dscm 2.49E-03 2.51E-03 2.43E-03 0.002 ng/dscm@7%O2 2.25E-03 2.27E-03 2.21E-03 0.002 

### Compound:3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber 1 2 3 Mass_mg 0.0000005 0.0000005 0.0000005 0.000 lb/mmBtuO2 5.20E-11 5.24E-11 5.10E-11 0.000 ng/dscm 6.23E-02 6.27E-02 6.06E-02 0.062 ng/dscm@7%O2 5.62E-02 5.66E-02 5.51E-02 0.056 

### Compound:3,3',4,4',5-PeCB (PCB126) Average RunNumber 1 2 3 Mass_mg 0.0000005 0.0000005 0.0000005 0.000 lb/mmBtuO2 5.20E-11 5.24E-11 5.10E-11 0.000 ng/dscm 6.23E-02 6.27E-02 6.06E-02 0.062 ng/dscm@7%O2 5.62E-02 5.66E-02 5.51E-02 0.056 

### Compound:3,3',4,4'-TCB (PCB77) Average RunNumber 1 2 3 Mass_mg 0.0000005 0.0000005 0.0000005 0.000 lb/mmBtuO2 5.20E-11 5.24E-11 5.10E-11 0.000 ng/dscm 6.23E-02 6.27E-02 6.06E-02 0.062 ng/dscm@7%O2 5.62E-02 5.66E-02 5.51E-02 0.056 

### Compound:3,4,4',5-TCB (PCB81) Average RunNumber 1 2 3 Mass_mg 0.0000005 0.0000005 0.0000005 0.000 lb/mmBtuO2 5.20E-11 5.24E-11 5.10E-11 0.000 ng/dscm 6.23E-02 6.27E-02 6.06E-02 0.062 ng/dscm@7%O2 5.62E-02 5.66E-02 5.51E-02 0.056 

### Compound:OCDD Average RunNumber 1 2 3 Mass_mg 0.0000002 0.0000002 0.0000002 0.000 lb/mmBtuO2 2.08E-11 2.09E-11 2.04E-11 0.000 ng/dscm 2.49E-02 2.51E-02 2.43E-02 0.025 ng/dscm@7%O2 2.25E-02 2.27E-02 2.21E-02 0.022 

### Compound:OCDF Average RunNumber 1 2 3


### Sunday, January 30, 2011 Page 8 of 12

### Minnkota Power Cooperative Inc.

Mass_mg 0.0000002 0.0000002 0.0000002 0.000 lb/mmBtuO2 2.08E-11 2.09E-11 2.04E-11 0.000 ng/dscm 2.49E-02 2.51E-02 2.43E-02 0.025 ng/dscm@7%O2 2.25E-02 2.27E-02 2.21E-02 0.022 

### Compound:Other HpCDD Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:Other HpCDF Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:Other HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:Other HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:Other PeCDD Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011 

### Compound:Other PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 1.04E-11 1.05E-11 1.02E-11 0.000 ng/dscm 1.25E-02 1.25E-02 1.21E-02 0.012 ng/dscm@7%O2 1.13E-02 1.13E-02 1.10E-02 0.011



### Sunday, January 30, 2011 Page 9 of 12

### Minnkota Power Cooperative Inc.

Process Run Data Compound:Other TCDD Average RunNumber 1 2 3 Mass_mg 0.00000002 0.00000002 0.00000002 0.000 lb/mmBtuO2 2.08E-12 2.09E-12 2.04E-12 0.000 ng/dscm 2.49E-03 2.51E-03 2.43E-03 0.002 ng/dscm@7%O2 2.25E-03 2.27E-03 2.21E-03 0.002 

### Compound:Other TCDF Average RunNumber 1 2 3 Mass_mg 0.000000046 0.0000001 0.00000002 0.000 lb/mmBtuO2 4.79E-12 1.05E-11 2.04E-12 0.000 ng/dscm 5.73E-03 1.25E-02 2.43E-03 0.007 ng/dscm@7%O2 5.17E-03 1.13E-02 2.21E-03 0.006



### Sunday, January 30, 2011 Page 10 of 12

### Minnkota Power Cooperative Inc.

Process Run Data

APCD Run Data

Process Lab Run Data 

### Run Name Value UOM Comments Target Value 1 Heat Input 2433.2 Million Btus/million BTU using O2 2500


### 2Heat Input 2455.9 Million Btus/million BTU using O2 2500
3Heat Input 2358.1 Million Btus/million BTU using O2 2500



### Sunday, January 30, 2011 Page 11 of 12

### Minnkota Power Cooperative Inc.

Sampling / Stack Data Results Detail



### LocationUnit 1 - Method 23 Average Run Number 1 2 3 Test Date 5/18/2010 5/19/2010 5/20/2010 Run Start Time 8:05:00 AM7:30:00 AM6:56:00 AM Run Finish Time 5:01:30 PM3:54:00 PM3:22:00 PM Net Traversing Points 36 48 48 Net Run Time, minutes 486 480 480 Nozzle Diameter, inches 0.22 0.22 0.22 0.220 Pitot Tube Coefficient 0.827 0.827 0.827 0.827 Dry Gas Meter Calibration Factor 1.002 1.002 1.002 1.002 Barometric Pressure, inches of Mercury 27.63 27.7 27.7 27.677 Average Orifice Meter Differential, inches H2O 1.14 1.25 1.29 1.227 Dry Gas Meter Volume Sampled, cubic feet 314.910 306.076 315.367 312.118 Average Dry Gas Meter Temperature, °F 84.18 73.86 72.26 76.767 Dry Gas Meter Volume Sampled, dscf 283.583 281.748 291.204 285.512 Total Moisture Liquid collected, g 1076.3 1075.4 1106.61,086.100 Volume of Water Vapor, standard cubic feet 50.66 50.62 52.09 51.123 Moisture Content of Stack Gas, % 15.16 15.23 15.17 15.187 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8484 0.8477 0.8483 0.848 Carbon Dioxide, % 14.4 14.6 14.5 14.500 Oxygen, % 5.5 5.5 5.6 5.533 Carbon Monoxide & Nitrogen, % 80.1 79.9 79.9 79.967 Fuel Factor 1.07 1.05 1.06 Dry Molecular Weight, lb/lb-Mole 30.52 30.56 30.54 30.540 Wet Molecular weight, lb/lb-Mole 28.62 28.65 28.64 28.637 Flue Gas Static Pressure, inches of H2O -0.75 -0.8 -0.77 -0.773 Absolute Flue Gas Pressure, inches of Mercury 27.57 27.64 27.64 27.617 Average Stack Gas Temperature, °F 333.22 337.92 334.15 335.097 Average Velocity Head, inches of H2O 0.9863388709 432531.072770053

756141.107793207

49708 1.056
Average Stack Gas Velocity, feet/second 70.40 73.51 74.53 72.813 Stack Cross-Sectional Area, square feet 283.529 283.529 283.529 283.529 Dry Volumetric Flow Rate, dry scfm 623,214.4 648,019.9 660,597.9643,944.067 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,197,626.51,250,533.01,267,885.01,238,681.5 00 Percent Isokinetic of Sampling Rate, % 100.6 97.3 98.6 98.833 Percent Excess Air, % 35.2 35.3 36.1 35.533 F-Factor, dscfm/MMBtu @ %O2 9860 9860 98609,860.000 Round Duct Diameter, inches 228 228 228 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 11950 11950 1195011,950.000 Fc 1910 1910 19101,910.000



### Sunday, January 30, 2011 Page 12 of 12