InstructionsforCompletingtheProcessDataTemplateThistemplateistobeusedtorecordthe30dailyaveragesofspecificprocessdatarequiredbytheICR.TheERTdoesnothavethecapabilitytostorethesedailyaverages.Thisspreadsheetincluded4separatesurrogateworksheets,incasetheInstructionsforCompletingtheProcessDataTemplateThistemplateistobeusedtorecordthe30dailyaveragesofspecificprocessdatarequiredbytheICR.TheERTdoesnothavethecapabilitytostorethesedailyaverages.Thisspreadsheetincluded4separatesurrogateworksheets,incasetheboilertestedistestedforallsurrogatesat4differentdates.Thisspreadsheetisintendedtobeusedforoneboilerofonefacility.Dataformultipleboilersshouldbehandledbyusingseparatecopiesofthisspreadsheet.Fieldsshadedinyellowarerequired(ifapplicabletoyourboilers'operation).Youdonotneedtopopulatecellsshadedingray,astheyareautomaticallypopulatedfromtheBoilerInformationworksheet.PleaseDoNotmodifythestructureofthisspreadsheetbyaddingorsubtractingrows,columns,cells.Pleasenameeachresultingspreadsheetwiththefollowingnamingconvention:[FacilityID] Unit [BoilerID] Processdata xls(example:8100 Unit 2 Processdata xls)InstructionsforCompletingtheProcessDataTemplateThistemplateistobeusedtorecordthe30dailyaveragesofspecificprocessdatarequiredbytheICR.TheERTdoesnothavethecapabilitytostorethesedailyaverages.Thisspreadsheetincluded4separatesurrogateworksheets,incasetheboilertestedistestedforallsurrogatesat4differentdates.Thisspreadsheetisintendedtobeusedforoneboilerofonefacility.Dataformultipleboilersshouldbehandledbyusingseparatecopiesofthisspreadsheet.Fieldsshadedinyellowarerequired(ifapplicabletoyourboilers'operation).Youdonotneedtopopulatecellsshadedingray,astheyareautomaticallypopulatedfromtheBoilerInformationworksheet.PleaseDoNotmodifythestructureofthisspreadsheetbyaddingorsubtractingrows,columns,cells.Pleasenameeachresultingspreadsheetwiththefollowingnamingconvention:[FacilityID]_Unit_[BoilerID]_Processdata.xls(example:8100_Unit_2_Processdata.xls).Pleaserefertothefollowingstepswhenusingthesespreadsheets.BoilerInformationWorksheetInstructionsforCompletingtheProcessDataTemplateThistemplateistobeusedtorecordthe30dailyaveragesofspecificprocessdatarequiredbytheICR.TheERTdoesnothavethecapabilitytostorethesedailyaverages.Thisspreadsheetincluded4separatesurrogateworksheets,incasetheboilertestedistestedforallsurrogatesat4differentdates.Thisspreadsheetisintendedtobeusedforoneboilerofonefacility.Dataformultipleboilersshouldbehandledbyusingseparatecopiesofthisspreadsheet.Fieldsshadedinyellowarerequired(ifapplicabletoyourboilers'operation).Youdonotneedtopopulatecellsshadedingray,astheyareautomaticallypopulatedfromtheBoilerInformationworksheet.PleaseDoNotmodifythestructureofthisspreadsheetbyaddingorsubtractingrows,columns,cells.Pleasenameeachresultingspreadsheetwiththefollowingnamingconvention:[FacilityID]_Unit_[BoilerID]_Processdata.xls(example:8100_Unit_2_Processdata.xls).Pleaserefertothefollowingstepswhenusingthesespreadsheets.BoilerInformationWorksheetPleaseentertheEIAFacilityCode,FacilityNameandBoilerIDofyourboilerontheBoilerInformationworksheet.ProcessDataWorksheetsPleaseuseoneprocessdataworksheetforeachHAPsurrogateevenissimultaneoustestingofdifferentHAPsurrogatesInstructionsforCompletingtheProcessDataTemplateThistemplateistobeusedtorecordthe30dailyaveragesofspecificprocessdatarequiredbytheICR.TheERTdoesnothavethecapabilitytostorethesedailyaverages.Thisspreadsheetincluded4separatesurrogateworksheets,incasetheboilertestedistestedforallsurrogatesat4differentdates.Thisspreadsheetisintendedtobeusedforoneboilerofonefacility.Dataformultipleboilersshouldbehandledbyusingseparatecopiesofthisspreadsheet.Fieldsshadedinyellowarerequired(ifapplicabletoyourboilers'operation).Youdonotneedtopopulatecellsshadedingray,astheyareautomaticallypopulatedfromtheBoilerInformationworksheet.PleaseDoNotmodifythestructureofthisspreadsheetbyaddingorsubtractingrows,columns,cells.Pleasenameeachresultingspreadsheetwiththefollowingnamingconvention:[FacilityID]_Unit_[BoilerID]_Processdata.xls(example:8100_Unit_2_Processdata.xls).Pleaserefertothefollowingstepswhenusingthesespreadsheets.BoilerInformationWorksheetPleaseentertheEIAFacilityCode,FacilityNameandBoilerIDofyourboilerontheBoilerInformationworksheet.ProcessDataWorksheetsPleaseuseoneprocessdataworksheetforeachHAPsurrogateevenissimultaneoustestingofdifferentHAPsurrogateswasdone.

# EIA Facility Cod e Facility Name Boiler ID 6016 Duck Creek 1

# EIA Facility Cod e Facility Name Boiler ID 6016 Duck Creek 1

Daily Average Process Data for a 30 Day Period Including the Testing D Date Coal Firing Rate Coal Firing Rate (units) Synfuel Firing Rate Day 1 5/12/2010 435.3 ton/hr Day 2 5/13/2010 424.5 ton/hr Day 3 5/14/2010 442.2 ton/hr Day 4 5/15/2010 431.4 ton/hr Day 5 5/16/2010 408.6 ton/hr Day 6 5/17/2010 406.3 ton/hr Day 7 5/18/2010 399.5 ton/hr Day 8 5/19/2010 392.5 ton/hr Day 9 5/20/2010 428.5 ton/hr Day 10 5/21/2010 415.0 ton/hr Day 11 5/22/2010 419.9 ton/hr Day 12 5/23/2010 383.8 ton/hr Day 13 5/24/2010 421.9 ton/hr Day 14 5/25/2010 442.4 ton/hr Day 15 5/26/2010 429.2 ton/hr Day 16 5/27/2010 425.0 ton/hr Day 17 5/28/2010 413.5 ton/hr Day 18 5/29/2010 414.7 ton/hr Day 19 5/30/2010 412.1 ton/hr Day 20 5/31/2010 402.0 ton/hr Day 21 6/1/2010 402.7 ton/hr Day 22 6/2/2010 381.9 ton/hr Day 23 6/3/2010 272.3 ton/hr Day 24 6/4/2010 293.8 ton/hr Day 25 6/5/2010 140.4 ton/hr Day 26 6/6/2010 335.4 ton/hr Day 27 6/7/2010 397.7 ton/hr Day 28 6/8/2010 395.9 ton/hr Day 29 6/9/2010 405.0 ton/hr Day 30 6/10/2010 404.4 ton/hr

# D at e Synfuel Firing Rate (units) Pet Coke Firing Rate Pet Coke Firing Rate (units) Coal Gas Firing Rate

# Coal Gas Firing Rate (units) Fuel oil Firing Rate Fuel oil Firing Rate (units)

# Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr) 4446.5 2911.4 4373.2 2838.2 4598.7 2973.7 4424.2 2881.6 4135.0 2715.5 4059.0 2684.5 3932.2 2587.9 3933.1 2530.7 4375.4 2837.2 4244.8 2784.8 4378.5 2858.1 4091.9 2647.0 4494.7 2878.9 4690.4 2982.3 4454.9 2874.6 4471.3 2838.4 4322.2 2756.6 4302.6 2778.6 4304.3 2823.0 4163.5 2711.8 4166.2 2732.3 3970.0 2619.8 2833.8 1866.1 3103.9 2044.5 1590.2 1014.9 3567.0 2320.9 4236.8 2727.0 4245.8 2705.8 4337.7 2770.7 4350.0 2748.1

# Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe) 404.1 441.1 395.2 430.6 411.3 448.0 398.4 435.3 374.8 409.4 371.6 406.2 359.9 393.7 351.6 384.9 393.6 430.1 388.1 423.2 395.0 430.3 363.6 397.3 397.7 433.3 414.5 452.4 397.2 433.5 393.5 429.3 379.5 414.8 383.3 418.1 384.9 420.7 372.7 407.0 374.7 409.2 358.2 391.8 247.3 273.3 273.2 299.7 125.6 142.0 312.5 342.8 372.8 407.1 374.0 409.3 380.8 416.0 377.1 412.4

# Control Device Operating Parameters, As Appicabl e Flue Gas Flow Rate (dscfm) Pressure Drop across FGD (in H2O) 9.3 8.9 9.5 9.2 8.6 8.3 7.8 7.8 9.3 8.9 8.9 7.8 8.8 9.4 9.5 9.3 9.0 8.9 9.1 8.7 8.7 8.2 5.4 6.5 4.0 6.7 9.0 9.0 9.1 9.2

# FGD Scrubber Liquor Flow Rate (gals/min) Sorbent Type Sorbent Injection Rate (lb/hr)

# Other Boiler or Control Device Operating Parameters (e.g., Boiler O2) Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

# Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%) 4.0 3.9 4.0 4.0 4.1 4.0 4.0 4.3 4.2 4.0 3.9 4.1 4.1 4.2 4.1 4.1 4.2 4.0 3.9 4.0 4.1 4.1 4.5 6.9 11.3

4.2 4.1 4.0 3.9 4.1

# Turbine Throttle Pressure (psig) Final Superheat Average Temperature (°F) 2400.1 1005.0 2399.8 1005.0 2400.3 1004.4 2399.7 1004.8 2399.4 1005.0 2400.0 1005.0 2399.6 1005.1 2400.0 1004.9 2400.0 1005.0 2399.8 1005.0 2400.0 1005.0 2396.7 1005.0 2400.0 1005.0 2399.9 1005.0 2399.9 1005.0 2400.1 1005.0 2400.0 1005.0 2400.2 1005.0 2399.5 1005.0 2399.3 1005.1 2400.2 1004.9 2399.2 1005.2 2397.7 1005.0 2217.9 955.5 1390.6 799.2 2400.1 1005.0 2400.4 1004.5 2399.9 1005.0 2400.0 1005.0 2399.9 1005.0

# Hot Reheat Pressure (psig) Average Hot Reheat Temperature (°F) 440.2 991.1 428.7 986.9 447.2 993.7 433.8 987.4 406.2 979.3 402.9 980.0 385.4 983.9 377.6 981.7 428.8 988.8 423.0 985.1 430.1 987.7 393.1 974.7 433.0 988.0 453.7 998.9 431.5 990.2 427.3 992.9 413.5 984.9 416.5 983.1 419.4 982.1 403.1 980.0 406.2 976.4 390.4 976.4 269.4 929.7 297.9 954.1 139.3 838.9 335.2 941.6 406.7 982.4 408.6 984.8 417.5 984.0 413.4 981.9

# SCR Ammonia Vapor Flow Rate (lb/hr) SCR Catalyst Pressure Drop (in H2O) 549.1 4.5 540.5 4.3 589.8 4.6 560.9 4.4 516.3 4.1 516.2 4.1 503.1 3.9 507.2 3.9 564.9 4.5 520.0 4.4 522.0 4.4 467.8 4.0 562.2 4.5 640.1 4.8 577.2 4.6 550.8 4.5 530.5 4.3 510.3 4.3 541.6 4.4 523.7 4.3 505.6 4.3 481.9 4.1 329.4 2.6 359.4 3.2

87.2 1.1 376.9 3.4 491.3 4.3 493.1 4.4 490.5 4.6 503.9 4.6

# Total Precipitator Power (KW) Absorber Pressure Drop (in H2O) A bsorber Slurry pH 1019.5 9.3 5.9 1017.4 8.9 5.8 1015.6 9.5 5.8 1028.9 9.2 5.8 1030.2 8.6 5.8 1035.7 8.3 5.8 1049.1 7.8 5.8 1050.8 7.8 5.8 1021.7 9.3 5.8 1020.7 8.9 5.8 1005.2 8.9 5.8 1020.6 7.8 5.8 1002.8 8.8 5.9 1009.4 9.4 5.9

984.0 9.5 5.9 979.1 9.3 5.8 970.2 9.0 5.9 967.8 8.9 5.9 956.4 9.1 5.9 981.2 8.7 5.9 976.3 8.7 5.9 961.9 8.2 5.8 993.8 5.4 5.8 871.2 6.5 5.9 760.4 4.0 7.2 974.0 6.7 5.9 948.2 9.0 5.9 945.4 9.0 5.9 929.2 9.1 5.9 930.8 9.2 5.8

# Absorber Slurry Density (lb/ft3 ) ID Fans Total Gas Flow (SCFM) A ir Heater outlet temp (F) 70.9 1007806.0 326.1 71.0 980082.2 325.5 71.4 1025154.7 325.2 71.7 1000400.9 322.8 71.9 949082.8 314.7 72.0 937906.1 318.1 72.1 905632.3 318.6 72.1 902231.7 316.6 72.2 1000959.1 323.0 72.3 967165.7 324.8 72.4 970593.1 330.3 72.2 901507.4 330.4 72.3 981693.9 339.6 72.3 1036470.1 335.6 72.2 997680.3 331.6 72.4 975423.2 330.5 72.5 945865.0 322.2 72.4 941424.8 325.5 72.5 951265.0 331.4 72.5 932842.5 325.4 72.6 932565.4 329.0 72.6 888415.3 319.2 71.7 654941.3 293.5 71.3 716304.8 312.8 70.9 561960.6 281.4 70.7 798185.4 307.8 71.0 939360.4 327.3 71.7 943173.8 328.6 72.2 954281.6 326.7 72.5 956614.2 331.9

# Scrubber Recycle Pump A (amps) Scrubber Recycle Pump B (amps) 91.2 80.9

9.1 80.8 0.0 80.8 0.0 80.7 0.0 80.9 0.0 81.1 0.0 81.2 0.0 81.2 0.0 81.7 0.0 81.6 0.0 81.4 0.0 14.2 0.0 0.0 0.0 0.0 0.0 71.7 0.0 81.0 0.0 81.3 0.0 81.2 0.0 81.2 0.0 81.6 0.0 81.6 0.0 81.7 0.0 81.2 6.6 73.2 90.6 80.0 91.4 79.3 91.4 0.0 91.8 0.0 92.0 0.0 92.2 0.0

# Scrubber Recycle Pump C (amps) Scrubber Recycle Pump D (amps) 72.3 0.0 72.1 0.0 72.2 0.0 72.1 0.0 72.2 0.0 72.3 0.0 72.3 0.0 72.2 0.0 72.7 0.0 72.7 0.0 72.6 0.0 72.2 63.4 72.2 76.4 72.2 76.4

8.4 76.2 0.0 76.4 0.0 76.7 0.0 76.6 0.0 76.8 0.0 77.0 0.0 77.0 0.0 77.1 0.0 76.4 0.0 62.6 0.0 28.7 0.0 76.0 0.0 76.1 0.0 76.5 0.0 76.7 0.0 76.8

# Scrubber Recycle Pump E (amps) 0.0 82.0 90.2 90.0 90.1 90.3 90.2 90.0 90.8 90.8 90.8 90.7 90.7 90.7 90.2 90.4 90.9 90.7 90.9 91.1 91.1 91.3 90.3 74.0

0.0 1.9 89.8 90.7 91.0 91.0

# EIA Facility Code Facility Name Boiler ID 6016 Duck Creek 1

Daily Average Process Data for a 30 Day Period Including the Testing D Date Coal Firing Rate Coal Firing Rate (units) Synfuel Firing Rate Day 1 Day 2 Day 3 Day 4 Day 5 Day 6 Day 7 Day 8 Day 9 Day 10 Day 11 Day 12 Day 13 Day 14 Day 15 Day 16 Day 17 Day 18 Day 19 Day 20 Day 21 Day 22 Day 23 Day 24 Day 25 Day 26 Day 27 Day 28 Day 29 Day 30

# D at e Synfuel Firing Rate (units) Pet Coke Firing Rate Pet Coke Firing Rate (units) Coal Gas Firing Rate

# Coal Gas Firing Rate (units) Fuel oil Firing Rate Fuel oil Firing Rate (units)

# Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr)

# Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe)

# Control Device Operating Parameters, As Appicable Flue Gas Flow Rate (dscfm) Pressure Drop across FGD (in H2O)

# FGD Scrubber Liquor Flow Rate (gals/min) Sorbent Type Sorbent Injection Rate (lb/hr)

# Other Boiler or Control Device Operating Parameters (e.g., Boiler O2) Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

# Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%)

# Flue Gas Moisture Content (%)

# EIA Facility Code Facility Name Boiler ID 6016 Duck Creek 1

Daily Average Process Data for a 30 Day Period Including the Testing D Date Coal Firing Rate Coal Firing Rate (units) Synfuel Firing Rate Day 1 Day 2 Day 3 Day 4 Day 5 Day 6 Day 7 Day 8 Day 9 Day 10 Day 11 Day 12 Day 13 Day 14 Day 15 Day 16 Day 17 Day 18 Day 19 Day 20 Day 21 Day 22 Day 23 Day 24 Day 25 Day 26 Day 27 Day 28 Day 29 Day 30

# D at e Synfuel Firing Rate (units) Pet Coke Firing Rate Pet Coke Firing Rate (units) Coal Gas Firing Rate

# Coal Gas Firing Rate (units) Fuel oil Firing Rate Fuel oil Firing Rate (units)

# Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr)

# Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe)

# Control Device Operating Parameters, As Appicable Flue Gas Flow Rate (dscfm) Pressure Drop across FGD (in H2O)

# FGD Scrubber Liquor Flow Rate (gals/min) Sorbent Type Sorbent Injection Rate (lb/hr)

# Other Boiler or Control Device Operating Parameters (e.g., Boiler O2) Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

# Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%)

# Flue Gas Moisture Content (%)

# EIA Facility Code Facility Name Boiler ID 6016 Duck Creek 1

Daily Average Process Data for a 30 Day Period Including the Testing D Date Coal Firing Rate Coal Firing Rate (units) Synfuel Firing Rate Day 1 5/12/2010 435.3 ton/hr Day 2 5/13/2010 424.5 ton/hr Day 3 5/14/2010 442.2 ton/hr Day 4 5/15/2010 431.4 ton/hr Day 5 5/16/2010 408.6 ton/hr Day 6 5/17/2010 406.3 ton/hr Day 7 5/18/2010 399.5 ton/hr Day 8 5/19/2010 392.5 ton/hr Day 9 5/20/2010 428.5 ton/hr Day 10 5/21/2010 415.0 ton/hr Day 11 5/22/2010 419.9 ton/hr Day 12 5/23/2010 383.8 ton/hr Day 13 5/24/2010 421.9 ton/hr Day 14 5/25/2010 442.4 ton/hr Day 15 5/26/2010 429.2 ton/hr Day 16 5/27/2010 425.0 ton/hr Day 17 5/28/2010 413.5 ton/hr Day 18 5/29/2010 414.7 ton/hr Day 19 5/30/2010 412.1 ton/hr Day 20 5/31/2010 402.0 ton/hr Day 21 6/1/2010 402.7 ton/hr Day 22 6/2/2010 381.9 ton/hr Day 23 6/3/2010 272.3 ton/hr Day 24 6/4/2010 293.8 ton/hr Day 25 6/5/2010 140.4 ton/hr Day 26 6/6/2010 335.4 ton/hr Day 27 6/7/2010 397.7 ton/hr Day 28 6/8/2010 395.9 ton/hr Day 29 6/9/2010 405.0 ton/hr Day 30 6/10/2010 404.4 ton/hr

# D at e Synfuel Firing Rate (units) Pet Coke Firing Rate Pet Coke Firing Rate (units) Coal Gas Firing Rate

# Coal Gas Firing Rate (units) Fuel oil Firing Rate Fuel oil Firing Rate (units)

# Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr) 4446.5 2911.4 4373.2 2838.2 4598.7 2973.7 4424.2 2881.6 4135.0 2715.5 4059.0 2684.5 3932.2 2587.9 3933.1 2530.7 4375.4 2837.2 4244.8 2784.8 4378.5 2858.1 4091.9 2647.0 4494.7 2878.9 4690.4 2982.3 4454.9 2874.6 4471.3 2838.4 4322.2 2756.6 4302.6 2778.6 4304.3 2823.0 4163.5 2711.8 4166.2 2732.3 3970.0 2619.8 2833.8 1866.1 3103.9 2044.5 1590.2 1014.9 3567.0 2320.9 4236.8 2727.0 4245.8 2705.8 4337.7 2770.7 4350.0 2748.1

# Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe) 404.1 441.1 395.2 430.6 411.3 448.0 398.4 435.3 374.8 409.4 371.6 406.2 359.9 393.7 351.6 384.9 393.6 430.1 388.1 423.2 395.0 430.3 363.6 397.3 397.7 433.3 414.5 452.4 397.2 433.5 393.5 429.3 379.5 414.8 383.3 418.1 384.9 420.7 372.7 407.0 374.7 409.2 358.2 391.8 247.3 273.3 273.2 299.7 125.6 142.0 312.5 342.8 372.8 407.1 374.0 409.3 380.8 416.0 377.1 412.4

# Control Device Operating Parameters, As Appicable Flue Gas Flow Rate (dscfm) Pressure Drop across FGD (in H2O) 9.3 8.9 9.5 9.2 8.6 8.3 7.8 7.8 9.3 8.9 8.9 7.8 8.8 9.4 9.5 9.3 9.0 8.9 9.1 8.7 8.7 8.2 5.4 6.5 4.0 6.7 9.0 9.0 9.1 9.2

# FGD Scrubber Liquor Flow Rate (gals/min) Sorbent Type Sorbent Injection Rate (lb/hr)

# Other Boiler or Control Device Operating Parameters (e.g., Boiler O2) Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

# Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%) 4.0 3.9 4.0 4.0 4.1 4.0 4.0 4.3 4.2 4.0 3.9 4.1 4.1 4.2 4.1 4.1 4.2 4.0 3.9 4.0 4.1 4.1 4.5 6.9 11.3

4.2 4.1 4.0 3.9 4.1

# Flue Gas Moisture Content (%) Turbine Throttle Pressure (psig) Final Superhea 2400.1 1005.0 2399.8 1005.0 2400.3 1004.4 2399.7 1004.8 2399.4 1005.0 2400.0 1005.0 2399.6 1005.1 2400.0 1004.9 2400.0 1005.0 2399.8 1005.0 2400.0 1005.0 2396.7 1005.0 2400.0 1005.0 2399.9 1005.0 2399.9 1005.0 2400.1 1005.0 2400.0 1005.0 2400.2 1005.0 2399.5 1005.0 2399.3 1005.1 2400.2 1004.9 2399.2 1005.2 2397.7 1005.0 2217.9 955.5 1390.6 799.2 2400.1 1005.0 2400.4 1004.5 2399.9 1005.0 2400.0 1005.0 2399.9 1005.0

# Hot Reheat Pressure (psig) Average Hot Reheat Te m SCR Ammonia Vapor Flo w 440.2 991.1 549.1 428.7 986.9 540.5 447.2 993.7 589.8 433.8 987.4 560.9 406.2 979.3 516.3 402.9 980.0 516.2 385.4 983.9 503.1 377.6 981.7 507.2 428.8 988.8 564.9 423.0 985.1 520.0 430.1 987.7 522.0 393.1 974.7 467.8 433.0 988.0 562.2 453.7 998.9 640.1 431.5 990.2 577.2 427.3 992.9 550.8 413.5 984.9 530.5 416.5 983.1 510.3 419.4 982.1 541.6 403.1 980.0 523.7 406.2 976.4 505.6 390.4 976.4 481.9 269.4 929.7 329.4 297.9 954.1 359.4 139.3 838.9 87.2 335.2 941.6 376.9 406.7 982.4 491.3 408.6 984.8 493.1 417.5 984.0 490.5 413.4 981.9 503.9

# SCR Catalyst Pressure Drop (in H2O) Total Precipitator Power (KW) 4.5 1019.5 4.3 1017.4 4.6 1015.6 4.4 1028.9 4.1 1030.2 4.1 1035.7 3.9 1049.1 3.9 1050.8 4.5 1021.7 4.4 1020.7 4.4 1005.2 4.0 1020.6 4.5 1002.8 4.8 1009.4 4.6 984.0 4.5 979.1 4.3 970.2 4.3 967.8 4.4 956.4 4.3 981.2 4.3 976.3 4.1 961.9 2.6 993.8 3.2 871.2 1.1 760.4 3.4 974.0 4.3 948.2 4.4 945.4 4.6 929.2 4.6 930.8

# Absorber Pressure Drop (in H2O) A bsorber Slurry pH A bsorber S ID Fans T o 9.3 5.9 70.9 ######## 8.9 5.8 71.0 980082.2 9.5 5.8 71.4 ######## 9.2 5.8 71.7 ######## 8.6 5.8 71.9 949082.8 8.3 5.8 72.0 937906.1 7.8 5.8 72.1 905632.3 7.8 5.8 72.1 902231.7 9.3 5.8 72.2 ######## 8.9 5.8 72.3 967165.7 8.9 5.8 72.4 970593.1 7.8 5.8 72.2 901507.4 8.8 5.9 72.3 981693.9 9.4 5.9 72.3 ######## 9.5 5.9 72.2 997680.3 9.3 5.8 72.4 975423.2 9.0 5.9 72.5 945865.0 8.9 5.9 72.4 941424.8 9.1 5.9 72.5 951265.0 8.7 5.9 72.5 932842.5 8.7 5.9 72.6 932565.4 8.2 5.8 72.6 888415.3 5.4 5.8 71.7 654941.3 6.5 5.9 71.3 716304.8 4.0 7.2 70.9 561960.6 6.7 5.9 70.7 798185.4 9.0 5.9 71.0 939360.4 9.0 5.9 71.7 943173.8 9.1 5.9 72.2 954281.6 9.2 5.8 72.5 956614.2

# Air Heater outlet temp (F) Scrubber Recycle Pump A (amps ) Scrubber Recycle Pump B (amps) 326.1 91.2 80.9 325.5 9.1 80.8 325.2 0.0 80.8 322.8 0.0 80.7 314.7 0.0 80.9 318.1 0.0 81.1 318.6 0.0 81.2 316.6 0.0 81.2 323.0 0.0 81.7 324.8 0.0 81.6 330.3 0.0 81.4 330.4 0.0 14.2 339.6 0.0 0.0 335.6 0.0 0.0 331.6 0.0 71.7 330.5 0.0 81.0 322.2 0.0 81.3 325.5 0.0 81.2 331.4 0.0 81.2 325.4 0.0 81.6 329.0 0.0 81.6 319.2 0.0 81.7 293.5 0.0 81.2 312.8 6.6 73.2 281.4 90.6 80.0 307.8 91.4 79.3 327.3 91.4 0.0 328.6 91.8 0.0 326.7 92.0 0.0 331.9 92.2 0.0

# Scrubber Recycle Pump C (amps) Scrubber Recycle Pump D (amp s Scrubber Recy c 72.3 0.0 0.0 72.1 0.0 82.0 72.2 0.0 90.2 72.1 0.0 90.0 72.2 0.0 90.1 72.3 0.0 90.3 72.3 0.0 90.2 72.2 0.0 90.0 72.7 0.0 90.8 72.7 0.0 90.8 72.6 0.0 90.8 72.2 63.4 90.7 72.2 76.4 90.7 72.2 76.4 90.7

8.4 76.2 90.2 0.0 76.4 90.4 0.0 76.7 90.9 0.0 76.6 90.7 0.0 76.8 90.9 0.0 77.0 91.1 0.0 77.0 91.1 0.0 77.1 91.3 0.0 76.4 90.3 0.0 62.6 74.0 0.0 28.7 0.0 0.0 76.0 1.9 0.0 76.1 89.8 0.0 76.5 90.7 0.0 76.7 91.0 0.0 76.8 91.0

# c le Pump E (amps)