### Name: Steve Carter

Title: Vice President Regulated Generation Company: Cleco Power, LLC Sign Date: Name: Chuck Bruffey Title: Program Manager Company:Shaw Environmental, Inc. Sign Date: 8/11/2010 Permitted Facility Representative / Date Testing Company Representative / Date Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Tuesday, March 01, 2011 Page 1 of 10

### Facility Information:

Dolet Hills
963 Power Plant Rd

Mansfield, DeSoto PLA Contact:Paul Turrengano Phone:318 484-7413 Fax: Email: Testing Company: Shaw Environmental, Inc.
4171 Essen Lane

Baton Rouge LA70809 Contact:Richard Ishikawa Phone:225 932-2745 Fax: 225 213-1274 Email:

Air Permit Number: 0760-00001-V1 Permitted Source ID/Name: 51 Permitted Maximum Process Rate:Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Boiler 1 uses an electrostatic precipitator and a wet scrubber for emission control.

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information: AFS #: FRS #:

SCC / Description10100301 External Combustion Boilers - Electric Generation - Lignite - Pulverized Coal: Dry Bottom, Wall Fired

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width Boiler 1 329.375 280 0 4 46 16 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location O2 Method 3A O2 3 120 0 Boiler 1 Co2 Method 3A CO2 3 120 0 Boiler 1



### Tuesday, March 01, 2011 Page 2 of 10

### Tuesday, March 01, 2011 Page 3 of 10

### Sampling / Stack Data Results Summary



### LocationBoiler 1 - Method 3A CO2 Average Run Number 1 2 3
Test Date 3/2/2010 3/2/2010 3/2/2010 Run Start Time 10:25:00 AM2:05:00 PM 5:25:00 PM Run Finish Time 1:46:00 PM5:03:00 PM 6:36:00 PM Carbon Dioxide, % 9.3 9.2 9.4 9.300 Oxygen, % 9.62 9.64 9.33 9.530 Dry Volumetric Flow Rate, dry scfm 0 0 0 0.000 F-Factor, dscfm/MMBtu @ %O2 9685 9418 9770 9,624.333 Moisture, % 0 0 0 0.000 Fuel Type Override Override Override
Fw 0 0 0.000
Fc 1910 0 0 636.667



### LocationBoiler 1 - Method 3A O2 Average Run Number 1 2 3
Test Date 3/2/2010 3/2/2010 3/2/2010 Run Start Time 10:25:00 AM2:05:00 PM 5:25:00 PM Run Finish Time 1:46:00 PM5:03:00 PM 6:36:00 PM Carbon Dioxide, % 9.3 9.2 9.4 9.300 Oxygen, % 9.62 9.64 9.33 9.530 Dry Volumetric Flow Rate, dry scfm 0 0 0 0.000 F-Factor, dscfm/MMBtu @ %O2 9685 9418 9770 9,624.333 Moisture, % 0 0 0 0.000 Fuel Type Override Override Override
Fw 0 0 0 0.000
Fc 0 0 0 0.000



### Tuesday, March 01, 2011 Page 4 of 10

### Emissions Summary



### Location: Stack Exit - Method 0011 Compound: Formaldehyde Average RunNumber M0011-1 M0011-2 M0011-3 Mass_mg 0.13 0.054 0.072 0.085 lb/mmBtuO2 4.62E-05 1.84E-05 2.45E-05 0.000 ppm 4.58E-02 1.81E-02 2.45E-02 0.029 ppm@7%O2 4.03E-02 1.60E-02 2.14E-02 0.026



### Location: Stack Exit - Method 25A Compound: Total organic compounds (TOC) as Average Run M25A-1 M25A-2 M25A-3 lb/mmBtuO2 5.10E-04 6.89E-04 3.47E-04 0.001 ppm 3.45E-01 4.62E-01 2.34E-01 0.347 ppm@7%O2 3.04E-01 4.09E-01 2.06E-01 0.306



### Location: Stack Exit - Method 26A Compound: Hydrogen Chloride Average RunNumber M26A-1 M26A-2 M26A-3 Mass_mg 0.38 0.37 0.25 0.333 Elb/hr 3.61E-03 3.52E-03 2.41E-03 0.003 lb/mmBtuO2 8.86E-05 8.40E-05 5.65E-05 0.000 mg/dscm 1.13E-01 1.09E-01 7.22E-02 0.098 mg/dscm@7%O2 9.70E-02 9.18E-02 6.16E-02 0.083 

### Compound: Hydrogen Fluoride Average RunNumber M26A-1 M26A-2 M26A-3 Mass_mg 0.25 0.25 0.25 0.250 Elb/hr 2.37E-03 2.38E-03 2.41E-03 0.002 lb/mmBtuO2 5.83E-05 5.68E-05 5.65E-05 0.000 mg/dscm 7.40E-02 7.34E-02 7.22E-02 0.073 mg/dscm@7%O2 6.35E-02 6.18E-02 6.16E-02 0.062



### Location: Stack Exit - Method 29 

### Compound: Antimony Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.001 0.001 0.001 0.001 Elb/hr 7.41E-06 7.37E-06 7.13E-06 0.000 lb/mmBtuO2 1.65E-07 1.68E-07 1.63E-07 0.000 mg/dscm 2.17E-04 2.20E-04 2.13E-04 0.000 mg/dscm@7%O2 1.81E-04 1.83E-04 1.77E-04 0.000 

### Compound: Arsenic Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.00167 0.00188 0.0017 0.002


### Tuesday, March 01, 2011 Page 5 of 10Elb/hr 1.24E-05 1.39E-05 1.21E-05 0.000 lb/mmBtuO2 2.76E-07 3.16E-07 2.77E-07 0.000 mg/dscm 3.62E-04 4.13E-04 3.62E-04 0.000 mg/dscm@7%O2 3.01E-04 3.44E-04 3.01E-04 0.000 

### Compound: Beryllium Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.00025 0.00025 0.00025 0.000 Elb/hr 1.85E-06 1.84E-06 1.78E-06 0.000 lb/mmBtuO2 4.14E-08 4.20E-08 4.07E-08 0.000 mg/dscm 5.41E-05 5.49E-05 5.33E-05 0.000 mg/dscm@7%O2 4.50E-05 4.57E-05 4.44E-05 0.000 

### Compound: Cadmium Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.000353 0.0006 0.000377 0.000 Elb/hr 2.62E-06 4.42E-06 2.69E-06 0.000 lb/mmBtuO2 5.84E-08 1.01E-07 6.14E-08 0.000 mg/dscm 7.64E-05 1.32E-04 8.03E-05 0.000 mg/dscm@7%O2 6.36E-05 1.10E-04 6.68E-05 0.000 

### Compound: Chromium Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.00943 0.01635 0.01515 0.014 Elb/hr 6.99E-05 1.21E-04 1.08E-04 0.000 lb/mmBtuO2 1.56E-06 2.75E-06 2.47E-06 0.000 mg/dscm 2.04E-03 3.59E-03 3.23E-03 0.003 mg/dscm@7%O2 1.70E-03 2.99E-03 2.69E-03 0.002 

### Compound: Cobalt Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.000382 0.000604 0.000406 0.000 Elb/hr 2.83E-06 4.45E-06 2.89E-06 0.000 lb/mmBtuO2 6.32E-08 1.01E-07 6.61E-08 0.000 mg/dscm 8.27E-05 1.33E-04 8.65E-05 0.000 mg/dscm@7%O2 6.88E-05 1.11E-04 7.20E-05 0.000 

### Compound: Lead Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.00079 0.00263 0.00163 0.002 Elb/hr 5.86E-06 1.94E-05 1.16E-05 0.000 lb/mmBtuO2 1.31E-07 4.42E-07 2.65E-07 0.000 mg/dscm 1.71E-04 5.78E-04 3.47E-04 0.000 mg/dscm@7%O2 1.42E-04 4.81E-04 2.89E-04 0.000 

### Compound: Manganese Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.00515 0.01376 0.01003 0.010


### Tuesday, March 01, 2011 Page 6 of 10

### Process Run Data Elb/hr 3.82E-05 1.01E-04 7.15E-05 0.000 lb/mmBtuO2 8.52E-07 2.31E-06 1.63E-06 0.000 mg/dscm 1.12E-03 3.02E-03 2.14E-03 0.002 mg/dscm@7%O2 9.32E-04 2.51E-03 1.78E-03 0.002 

### Compound: Nickel Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.0086 0.01422 0.00957 0.011 Elb/hr 6.37E-05 1.05E-04 6.82E-05 0.000 lb/mmBtuO2 1.42E-06 2.39E-06 1.56E-06 0.000 mg/dscm 1.86E-03 3.13E-03 2.04E-03 0.002 mg/dscm@7%O2 1.55E-03 2.61E-03 1.70E-03 0.002 

### Compound: Selenium Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.0053 0.00372 0.00879 0.006 Elb/hr 3.93E-05 2.74E-05 6.27E-05 0.000 lb/mmBtuO2 8.77E-07 6.25E-07 1.43E-06 0.000 mg/dscm 1.15E-03 8.18E-04 1.87E-03 0.001 mg/dscm@7%O2 9.57E-04 6.81E-04 1.56E-03 0.001



### Location: Stack Exit - OTM - 27/28 Compound: Filterable Particulate Average RunNumber M5B/OTM28-1 M5B/OTM28-2 M5B/OTM28-3 Mass_mg 31.6 17.3 26 24.967 lb/mmBtuO2 4.45E-03 2.42E-03 3.63E-03 0.004 

### Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber M5B/OTM28-1 M5B/OTM28-2 M5B/OTM28-3 Mass_mg 11.2 12 7.8 10.333 lb/mmBtuO2 1.58E-03 1.68E-03 1.09E-03 0.001 

### Compound: Organic Condensible Particulate Average RunNumber M5B/OTM28-1 M5B/OTM28-2 M5B/OTM28-3 Mass_mg 2.6 1.7 1.4 1.900 lb/mmBtuO2 3.67E-04 2.38E-04 1.96E-04 0.000 

### Compound: Total Particulate Average RunNumber M5B/OTM28-1 M5B/OTM28-2 M5B/OTM28-3 Mass_mg 45.4 31 35.2 37.200 lb/mmBtuO2 6.40E-03 4.34E-03 4.92E-03 0.005



### Tuesday, March 01, 2011 Page 7 of 10

### Process Run Data

APCD Run Data

Process Lab Run Data 

### Run Name Value UOM Comments Target Value 1 Steam Output 12413 Klb/day 3/2/10 0


### 1 Total Heat Input 166752MMBTU/day 3/2/10 0
1 Heat Input 0 Million Btus/hr 0



### Run Name Value UOM Comments Target Value 1 ELECTROSTATIC PRECIPITATOR 0 0


### 1 SPRAY SCRUBBER 0 0

Tuesday, March 01, 2011 Page 8 of 10

### Sampling / Stack Data Results Detail



### LocationBoiler 1 - Method 3A CO2 Average Run Number 1 2 3 Test Date 3/2/2010 3/2/2010 3/2/2010 Run Start Time 10:25:00 AM2:05:00 PM 5:25:00 PM Run Finish Time 1:46:00 PM5:03:00 PM 6:36:00 PM Carbon Dioxide, % 9.3 9.2 9.4 9.300 Oxygen, % 9.62 9.64 9.33 9.530 Fuel Factor 1.21 1.22 1.23 Dry Volumetric Flow Rate, dry scfm 0 0 0 0.000 F-Factor, dscfm/MMBtu @ %O2 9685 9418 97709,624.333 Moisture, % 0 0 0 0.000 Analyzer Make Analyzer Model Analyzer Serial Number Operating Range 0 0 0 0.000 Operating Units % % % No. Readings/Avg. 0 0 0 0.000 Calibration Set 0 0 0 0.000 Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response 0 0 0 0.000 Calibration Pre Zero Cylinder Bias 0 0 0 0.000 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response 0 0 0 0.000 Calibration Pre High Cylinder Bias 0 0 0 0.000 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response 0 0 0 0.000 Calibration Post Zero Cylinder Bias 0 0 0 0.000 Calibration Post Zero Cylinder Drift 0 0 0 0.000 Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response 0 0 0 0.000 Calibration Post High Cylinder Bias 0 0 0 0.000 Calibration Post High Cylinder Drift 0 0 0 0.000 Cavg 9.3 9.2 9.3 9.267 Cavg Units %vd %vd %vd Cgas Cgas Units %vd %vd %vd Fuel Type Override Override Override Fw 0 0 0.000 Fc 1910 0 0 636.667 Cgasw 0 0 0 0.000 Cgasw Units



### Tuesday, March 01, 2011 Page 9 of 10

### LocationBoiler 1 - Method 3A O2 Average

Run Number 1 2 3 Test Date 3/2/2010 3/2/2010 3/2/2010 Run Start Time 10:25:00 AM2:05:00 PM 5:25:00 PM Run Finish Time 1:46:00 PM5:03:00 PM 6:36:00 PM Carbon Dioxide, % 9.3 9.2 9.4 9.300 Oxygen, % 9.62 9.64 9.33 9.530 Fuel Factor 1.21 1.22 1.23 Dry Volumetric Flow Rate, dry scfm 0 0 0 0.000 F-Factor, dscfm/MMBtu @ %O2 9685 9418 97709,624.333 Moisture, % 0 0 0 0.000 Analyzer Make Analyzer Model Analyzer Serial Number Operating Range 0 0 0 0.000 Operating Units % % % No. Readings/Avg. 0 0 0 0.000 Calibration Set 0 0 0 0.000 Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response 0 0 0 0.000 Calibration Pre Zero Cylinder Bias 0 0 0 0.000 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response 0 0 0 0.000 Calibration Pre High Cylinder Bias 0 0 0 0.000 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response 0 0 0 0.000 Calibration Post Zero Cylinder Bias 0 0 0 0.000 Calibration Post Zero Cylinder Drift 0 0 0 0.000 Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response 0 0 0 0.000 Calibration Post High Cylinder Bias 0 0 0 0.000 Calibration Post High Cylinder Drift 0 0 0 0.000 Cavg 9.62 9.64 9.33 9.530 Cavg Units %vd %vd %vd Cgas Cgas Units %vd %vd %vd Fuel Type Override Override Override Fw 0 0 0 0.000 Fc 0 0 0 0.000 Cgasw 0 0 0 0.000 Cgasw Units



### Tuesday, March 01, 2011 Page 10 of 10