### RULE 212 STORAGE OF ORGANIC LIQUIDS

Adopted 5-24-77 (Amended 6-19-79, 9-25-90, 10-19-9 3, 11-03-94, 6-08-95, 6-19-97)

CONTENTS

100 GENERAL

101 PURPOSE

102 APPLICABILITY

200 DEFINITIONS

201 EFFICIENCY

202 EXEMPT COMPOUNDS

203 EXTERNAL FLOATING ROOF

204 INTERNAL FLOATING ROOF

205 METALLIC-SHOE-SEAL
206 ORGANIC LIQUID

207 PRESSURE TANK

208 RESILIENT-TOROID-SEAL

209 STORAGE TANK

210 VAPOR PRESSURE

211 VAPOR RECOVERY SYSTEM

212 VAPOR TIGHT 213 VOLATILE ORGANIC COMPOUNDS (VOC)

300 STANDARDS

301 STORAGE TANKS WITH A CAPACITY GREATER THAN 40,000 GALLONS

302 STORAGE TANKS WITH A CAPACITY LESS THAN OR EQUAL TO 40,000 GALLONS

303 STORAGE TANKS WITH A CAPACITY GREATER THAN 20,000 GALLONS AND LESS THAN OR EQUAL TO 40,000 GALLONS

304 ABOVE GROUND STORAGE TANKS WITH A CAPACITY GREATER THAN 10,000

GALLONS AND LESS THAN OR EQUAL TO 20,000 GALLONS

305 ANY STORAGE TANK CONTAINING ORGANIC LIQUIDS WITH A VAPOR

PRESSURE GREATER THAN 569 MM Hg (11 PSIA)

306 EXTERNAL FLOATING ROOF

307 INTERNAL FLOATING ROOF

308 VAPOR RECOVERY SYSTEM

309 CRITERIA FOR METALLIC-SHOE-SEAL CLOSURES

310 CRITERIA FOR WELDED TAN KS WITH METALLIC-SHOE-SEALS

311 CRITERIA FOR RIVETED TAN KS WITH METALLIC-SHOE-SEALS

312 CRITERIA FOR RESI LIENT-TOROID-SEAL

313 CRITERIA FOR WELDED TANKS WITH ZERO GAP SECONDARY SEALS

400 ADMINISTRATIVE REQUIREMENTS

401 PRIMARY SEAL INSPECTION

500 MONITORING AND RECORDS

501 RECORDKEEPING

502 TEST METHODS

June 19, 1997 Placer County APCD 212 - 1 Rules and RegulationsThis Page Intentionally Left Blank

June 19, 1997 Rules and Regulations 212 - 2 Placer County APCD100 GENERAL

101 PURPOSE: To limit emissions from storage tanks for organic liquids.

102 APPLICABILITY:

102.1 Geographic : The provisions of this rule apply to all of Placer County.

102.2 Business Function: This rule applies to any facility where organic liquids having a vapor pressure greater than 25.8 mm Hg (0.5 psia) are placed, stored, or held in any stationary tank, reserv oir or other bulk container.

200 DEFINITIONS

201 EFFICIENCY: A comparison of controlled emissi ons to those uncontrolled emissions

which would occur from a fixed or cone roof tank in the same product service without a vapor control system. Baseline emissions sha ll be calculated using the criteria in API

Bulletin 2518.

202 EXEMPT COMPOUNDS: Exempt Compounds are defined in Rule 102, Definitions

.

203 EXTERNAL FLOATING ROOF: A vapor loss control device, consisting of a pontoontype or double-deck-type cover that rests on the surface of the liquid contents and which is equipped with an approved closure device between the tank shell and roof edge.

204 INTERNAL FLOATING ROOF: A vapor loss control device consisting of a fixed roof with an internal-floating-type cover which prevents the release or emission to the atmosphere of organic vapors or gases at an efficiency equivalent to an approved external floating roof closure device.

205 METALLIC-SHOE-SEAL: A type of seal used to minimize evaporative losses of organic liquids from a storage tank equipped with an external floating roof. It serves a primary seal, and is constructed with vertical metal plates or "shoes", connected by braces or other devices to the circumference of the floating roof. They are partially immersed in the liquid being stored, and are suspended in su ch a way that they are forced outward against the inner tank wall.

206 ORGANIC LIQUID: Any volatile organic compound which contains hydrogen and which would exist as a liquid at actual conditions of use or storage.

207 PRESSURE TANK: A closed storage tank designed and constructed to (1) operate at internal pressures above one atmosphere, (2) be able to withstand the vapor pressure of the stored liquid under all storage conditions and (3) prevent at all times the loss of such material or its vapor to the atmosphere.

208 RESILIENT-TOROID-SEAL: A type of seal used to minimize evaporative losses of organic liquids from a storage tank equipped with an external floating roof. It is a toroidal tube, or "donut", made of fabric or other resilient material, that rests on the surface of the stored liquid. It serves as primary seal that minimizes evaporative losses from the tank. The toroid seal may be filled with air, foam, or other resilient material.

209 STORAGE TANK: Any stationary container, reservoir, or tank used for the storage of organic liquids.

210 VAPOR PRESSURE: The vapor pressure under actual storage conditions as determined by the test methods specified in Section 502.1.

June 19, 1997 Placer County APCD 212 - 3 Rules and Regulations211 VAPOR RECOVERY SYSTEM: A California Air Resources Board (CARB) - certified system that collects organic vapors and gase s from a storage tank and either returns them to the tank or otherwise processes th em to prevent or reduce emissions to the atmosphere.

212 VAPOR TIGHT: A condition when the concentrat ion of total hydrocarbons does not exceed 10,000 ppm (express ed as methane) above backgroun d, as determined by EPA Reference Method 21. Background shall be def ined as the ambient concentration of organic compounds determined at least three (3 ) meters upwind of the potential source and not influenced by any specific emissions source.

213 VOLATILE ORGANIC COMPOUNDS (VOC): Compounds which contain at least one atom of carbon, except for the Exempt Compounds.

300 STANDARDS

301 STORAGE TANKS WITH A CAPACITY GREATER THAN 40,000 GALLONS: A person shall not store any organic liquid having a vapor pressure greater than 25.8 mm Hg (0.5 psia), in any storage tank with a capacity gr eater than 40,000 gallons, unless such tank is (1) a pressure tank maintaining working pressures sufficient at all times to prevent organic vapor or gas loss to the atmospher e, or (2) designed and equipped with one of the vapor loss control devices as specified in Sections 306, 307, and 308 of this rule.

302 STORAGE TANKS WITH A CAPACITY LESS THAN OR EQUAL TO 40,000

GALLONS: A person shall not store any organic liquid having a vapor pressure greater than 25.8 mm Hg (0.5 psia), in any storage tank with a capacity less than or equal to 40,000 gallons, unless such tank is equipped with one of the following:

302.1 A submerged fill pipe.

302.2 An apparatus of efficiency equal to a submerged fill pipe and which has been approved by the Air Pollution Control Officer.

302.3 One of the vapor loss control dev ices that complies with the applicable requirements of Sections 306 through 313 of this rule.

303 STORAGE TANKS WITH A CAPACITY GREATER THAN 20,000 GALLONS AND LESS THAN OR EQUAL TO 40,000 GALLONS: A person shall not store any organic liquid having a vapor pressure greater than 77.5 mm Hg (1.5 psia) in any storage tank with a capacity greater than 20,000 gallons , but less than or equal to 40,000 gallons, unless such tank is (1) a pressure tank maintaining working pressures sufficient at all times to prevent organic vapor or gas loss to the atmosphere, or (2) designed and equipped with one of the vapor loss control devices as specified in Sections 306 through

313 of this rule.

304 ABOVE GROUND STORAGE TANKS WITH A CAPACITY GREATER THAN 10,000 GALLONS AND LESS THAN OR EQUAL TO 20,000 GALLONS: A person shall not store any organic liquid having a vapor pressure greater than 77.5 mm Hg (1.5 psia) in any above ground storage tank with a capacity greater than 10,000 gallons, but less than or equal to 20,000 gallons capacity, unless su ch tank is (1) equipped with a pressurevacuum valve which is set to operate at a pr essure within 10% of the maximum allowable working pressure of the tank, or at a pressure of at least 25.8 mm Hg (0.5 psia), or (2) equipped with a vapor loss control device as specified in Sections 306 through 313 of this

rule.

June 19, 1997 Rules and Regulations 212 - 4 Placer County APCD305 ANY STORAGE TANK CONTAINING ORGANIC LIQUIDS WITH A VAPOR

PRESSURE GREATER THAN 569 mm Hg (11 psia): A person shall not store organic liquid with a vapor pressure greater than 569 mm Hg (11 psia) in any storage tank unless such tank is (1) a pressure tank maintaining working pressures sufficient at all times to prevent organic vapor or gas loss to the atmosphere, or (2) designed and equipped with a vapor recovery system whic h meets the requirements of Section 308 of

this rule.

306 EXTERNAL FLOATING ROOF: This vapor loss control device, as defined in Section 203, shall be equipped with a closure device t hat consists of two seals, one above the other; the one below shall be referred to as the primary seal and the one above shall be referred to as the secondary seal. Seal designs shall be submitted to the Air Pollution

Control Officer and shall not be installed or used unless they are approved by the Air Pollution Control Officer as meeting the criteria set forth within this section and the applicable closure requirements of Sections 309 through 313 of this rule.

307 INTERNAL FLOATING ROOF: This vapor loss control device with a fixed external roof, as defined in Section 205, shall prevent t he release or emission to the atmosphere of organic vapors or gases at an efficiency equiva lent to a floating roof closure device which meets the applicable requirements of Sections 309 through 313 of this rule.

308 VAPOR RECOVERY SYSTEM:

308.1 Any installed vapor recovery system shall be a CARB certified vapor recovery system capable of collecting organic v apors and gases, and shall include a vapor return or disposal system capable of processing such vapors and gases to prevent their emission to the atmosphere, at an efficiency of at least 95 percent by weight, determined in accordance with the applicable test method of Section

502.2.

308.2 Any tank gauging or sampling device on a tank vented to the vapor recovery system shall be equipped with a vapor-ti ght cover which shall be closed at all times except during gauging or sampling.

308.3 All piping, valves and fittings shall be constructed and maintained in a vapor-tight condition, as defined in Section 212.

309 CRITERIA FOR METALLIC-SHOE-SEAL CLOSURES:

309.1 Metallic-shoe-type seals s hall be installed so that one end of the shoe extends into the stored liquid and the other end extends a minimum vertical distance of 61 cm (24 inches) above the stored liquid surface.

309.2 The geometry of the shoe shall be su ch that the maximum gap between the shoe and the tank shell is no greater than double the gap allowed by the seal gap criteria for a length of at least 46 cm (1 8 inches) in the vertical plane above the liquid surface.

309.3 There shall be no holes or tears in, or openings through the secondary seal or in the primary seal envelope surrounding the annular vapor space enclosed by the roof edge, stored liquid surface, shoe, and seal fabric.

309.4 The secondary seal shall extend from the roof to the tank shell and shall not be attached to the primary seal.

June 19, 1997 Placer County APCD 212 - 5 Rules and Regulations309.5 Any roof drain which opens directly in to the organic liquid content in the tank shall be provided with a slotted membrane fa bric cover, or equivalent, that covers at least 90% of the area of the opening.

309.6 All openings in the roof, except pr essure-vacuum valves, shall provide a projection below the liquid surface to pr event belching of liquid and to prevent entrained or formed organic vapor from es caping from the liquid contents of the tank and shall be equipped with a cover, seal or lid. The cover, seal, or lid shall at all times be in a closed position, with no measurable gap exceeding 0.32 cm (1/8 in.), except when the device or appurtenanc e is in use. Pressure-vacuum valves located in the roof shall be set to within ten percent of the maximum allowable working pressure of the roof.

310 CRITERIA FOR WELDED TANKS WITH METALLIC-SHOE-SEALS: Any welded tank

shell which uses a metallic-s hoe-type seal shall meet the following conditions:

310.1 No gap between the tank shell and the primary seal shall exceed 3.8 cm (1-1/2 inches). The cumulative length of all primary seal gaps exceeding 1.3 cm ( 2 inch) shall be not more than 10% of the circumference; the cumulative length of all primary seal gaps exceeding 0.32 cm (1/8 inch) shall not be more than 40 percent of the circumference. No contin uous gap greater than 0.32 cm (1/8 inch)

shall exceed 10% of the circumference of the tank.

310.2 No gap between the tank shell and the secondary seal shall exceed 1.3 cm ( 2 inch). The cumulative length of all secondary seal gaps exceeding 0.32 cm (1/8 inch) shall not exceed 5 percent of the circumference of the tank.

310.3 The secondary seal shall allow easy insertion of probes up to 3.8 cm (1-1/2 inches) in width in order to measure gaps in the primary seal.

311 CRITERIA FOR RIVETED TANKS WITH METALLIC-SHOE-SEALS: Any riveted tank

shell which uses a metallic -shoe-seal shall meet t he following conditions:

311.1 No gap between the tank shell and the primary seal shall exceed 6.4 cm (2-1/2 in.). The cumulative length of all primar y seal gaps exceeding 3.8 cm (1-1/2 in.)

shall not be more than 10% of the circumference.

311.2 The secondary seal shall consist of at least two sealing surfaces, such that the sealing surfaces prevent the emission of organic compounds around the rivets. Serrated sealing surfaces are allowable if the length of serration does not exceed 15.2 cm (6 in.). No gap between the tank shell and the secondary seal shall exceed 1.3 cm ( 2 in.). The cumulative length of all secondary seal gaps exceeding 0.32 cm (1/8 in.) shall not be more than 5% of the circumference.

311.3 The secondary seal shall allow easy insertion of probes up to 3.8 cm (1-1/2 inches) in width in order to measure gaps in the primary seal.

312 CRITERIA FOR RESILIENT-TOROID-SEAL: Any storage tank wh ich uses a resilienttoroid-type seal shall meet the following conditions:

312.1 No gap between the tank shell and the primary seal shall exceed 1.3 cm ( 2 inch). The cumulative length of all gaps exceeding 0.32 cm (1/8 inch) shall not be more

than 5% of the circumference.

June 19, 1997 Rules and Regulations 212 - 6 Placer County APCD312.2 No gap between the tank shell and the secondary seal shall exceed 1.3 cm ( 2 inch). The cumulative length of all gaps exceeding 0.32 cm (1/8 inch) shall not be

more than 5% of the circumference.

312.3 The secondary seal shall allow easy insertion of probes up to 1.3 cm ( 2 inch) in width in order to measure gaps in the primary seal.

312.4 There shall be no holes or tears in, or openings through the secondary seal or in the primary seal envelope surrounding the annular vapor space enclosed by the roof edge, stored liquid surface, shoe, and seal fabric.

313 CRITERIA FOR WELDED TANKS WITH ZERO GAP SECONDARY SEALS: Any welded tank shell which uses a zero gap secondary seal must meet the following

conditions:

313.1 No gap between the tank shell and the primary seal shall exceed 3.8 cm (1-1/2 inches). The cumulative length of all primary seal gaps exceeding 1.3 cm ( 2 inch)

shall be not more than 10% of the circum ference and the cumulative length of all primary seal gaps exceeding 0.32 cm (1/8 inch) shall not be more than 40% of the circumference. No continuous gap gr eater than 0.32 cm (1/8 inch) shall

exceed 10% of the circumference of the tank.

313.2 No gap between the tank shell and the secondary seal shall exceed 1.5 mm (0.06 in.). The cumulative length of all secondary seal gaps exceeding 0.5 mm (0.02 inch) shall not exceed 5% of the circumference of the tank, excluding gaps less than 5 cm (1.79 in.) from vertical weld seams.

313.3 The secondary seal must exert a posit ive pressure against the tank shell such

that the seal surface in contact with th e tank shell does not pull away from the tank shell more than the gaps allowed in Section 313.2.

400 ADMINISTRATIVE REQUIREMENTS

401 PRIMARY SEAL INSPECTION:

401.1 The primary seal envelope shall be made available for unobstructed inspection by the District on an annual basis at four locations selected along its circumference at random by the APCO. If the District detects one or more violations as a result of any such inspec tion, the District may require such further unobstructed inspection of the primary seal as may be necessary to determine

the seal condition for its entire circumfere nce. The District shall also have the authority to require more inspection locations if the inspector suspects the possibility of a cumulative gap criteria violation.

401.2 In addition, for tanks with secondary seals the primary seal envelope shall be made available for inspection by the Dist rict prior to the installation of the secondary seal. For tanks with secondary seals installed before June 19, 1979, the primary seal envelope shall be made available for unobstructed inspection by the District for its full length every 5 years after June 19, 1979, except that if the secondary seal is voluntarily removed by the owner or operator prior thereto, it shall be made available for such inspection at that time. The owner or operator shall provide notification to the Distri ct no less than 7 working days prior to voluntary removal of the secondary seal.

June 19, 1997 Placer County APCD 212 - 7 Rules and Regulations500 MONITORING AND RECORDS

501 RECORDKEEPING:

501.1 A person whose tanks are subject to this Rule shall keep an accurate record of liquids stored in such containers and the vapor pressure ranges of such liquids.

501.2 Accurate records of throughput and sto ck temperature shall also be maintained.

501.3 Records shall include the number of organic liquid storage tanks serviced and their respective capacities in gallons.

501.4 Records shall be retained for a period of at least 2 years, and shall be retained at least 5 years by sources subject to the requirements of Rule 507, Federal Operating Permit Program , and made available to the Air Pollution Control Officer on request.

501.5 In addition to the recordkeeping requirements specified herein, all applicable provisions of Rule 410, Recordkeeping for Volatile Organic Compounds

Emissions , shall be met.

502 TEST METHODS

502.1 Vapor Pressure Determination: The vapor pressure under actual storage conditions is determined by ASTM method D-2879-83 or ASTM method D-323-

82.

502.2 Vapor Recovery System Testing: The determination of the overall vapor recovery system efficiency required in Section 308 shall be made using the following test procedures, as applicable:

502.2.1 California Air Resources Board Test Method TP 202.1, A Determination of Emission Factor of Vapor Recovery Systems at Gasoline Bulk Plants @

.

502.2.2 California Air Resources Board Test Method TP 203.1, A Determination of Emission Factor of Vapor Recovery Systems at Gasoline Terminals @

.



### 502.3 Vapor-Tight Condition Testing: EPA Reference Method 21 shall be used to test for vapor-tight condition.

June 19, 1997 Rules and Regulations 212 - 8 Placer County APCD