Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Wednesday, February 16, 2011 Page 1 of 13
Facility Information:

IP&L Eagle Valley Generating Station

4040 Blue Bluff Road

Martinsville IN 46151

Contact: Kyle Noah

Phone: 317-439-1251

Fax: 765-342-2311

Email: kyle.noah@aes.com

Testing Company:

URS Corporation

1600 Perimeter Park Drive, Suite 400

Morrisville NC 27560

Contact:Brad Justus

Phone: 919-461-1326

Fax: 919-461-1415

Email: brad_justus@urscorp.com

Air Permit Number:

991

Permitted Source ID/Name:

Boiler 6

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Unit 6 is rated at 105 MW (summer, gross). The unit combusts bituminous coal and consists of a tangentially fired 

combustor equipped with low NOX burners and over-fire air (LNB/OFA) and an electrostatic precipitator (ESP) to 

reduce air emissions.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 110000396606 FRS #: 110000396606

SCC / Description 10100211 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Wet Bottom (Tangential) (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 18.1 0 0 0 145 37 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit % H2O Method 1 - 4 3 180 0

Stack Exit Carbon Monoxide Method 10 3 120 0

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Wednesday, February 16, 2011 Page 2 of 13
Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Other TCDD Method 23 0

Stack Exit Other PeCDD Method 23 0

Stack Exit Other HxCDD Method 23 0

Stack Exit Other HpCDD Method 23 0

Stack Exit Other TCDF Method 23 0

Stack Exit Other PeCDF Method 23 0

Stack Exit Other HxCDF Method 23 0

Stack Exit Other HpCDF Method 23 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Stack Exit Total PCBs Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 120 0

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 180 0

Organic Condensible 

Particulate

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Filterable PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Wednesday, February 16, 2011 Page 3 of 13
The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None

Filterable Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Stack Exit Selenium Method 29 3 240 0

Stack Exit Filterable Particulate Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Arsenic Method 29 3 240 0

Stack Exit O2 Method 3A O2 3 480 0

Stack Exit Co2 Method 3A CO2 3 480 0

Stack Exit Co2 Method 3A CO2 3 120 0

Stack Exit Co2 Method 3A CO2 3 240 0

Stack Exit O2 Method 3A O2 3 240 0

Stack Exit O2 Method 3A O2 3 120 0

Stack Exit Sulfur Dioxide Method 6C 3 180 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0

Wednesday, February 16, 2011 Page 4 of 13
Sampling / Stack Data Results Summary

Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 5/11/2010 5/11/2010 5/12/2010

Run Start Time 9:40:00 AM 4:35:00 PM 7:45:00 AM

Run Finish Time 3:55:00 PM 10:50:00 

PM

4:10:00 PM

Net Run Time, minutes 360 360 360

Dry Gas Meter Volume Sampled, dscf 190.511 187.431 194.649 190.864

Moisture Content of Stack Gas, % 9.13 9.21 7.72 8.687

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11.2 10.4 11.1 10.900

Oxygen, % 7.9 8.7 8.6 8.400

Average Stack Gas Temperature, °F 291.63 286.67 261.51 279.937

Dry Volumetric Flow Rate, dry scfm 1,518.3 1,532.4 1,620.0 1,556.900

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,448.9 2,457.5 2,387.8 2,431.400

Percent Isokinetic of Sampling Rate, % 100.0 97.4 95.7 97.700

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 16, 2011 Page 5 of 13
Location Stack Exit - OTM - 27/28

Average

Run Number 1 2 3

Test Date 5/11/2010 5/11/2010 5/12/2010

Run Start Time 7:45:00 AM 4:35:00 PM 7:45:00 AM

Run Finish Time 3:54:30 PM 10:03:30 

PM

3:54:30 PM

Net Run Time, minutes 335.75 344.25 335.25

Dry Gas Meter Volume Sampled, dscf 125.255 123.257 125.255 124.589

Moisture Content of Stack Gas, % 7.40 8.39 7.60 7.797

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11.2 10.4 11.1 10.900

Oxygen, % 7.9 8.7 8.6 8.400

Average Stack Gas Temperature, °F 262.17 277.83 262.17 267.390

Dry Volumetric Flow Rate, dry scfm 1,625.8 1,609.8 1,622.3 1,619.300

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,472.5 2,528.2 2,472.5 2,491.067

Percent Isokinetic of Sampling Rate, % 100.9 97.8 101.2 99.967

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 16, 2011 Page 6 of 13
Emissions Summary

Location: Stack Exit - Method 29 

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.0031 0.0044 0.0044039 0.004

Elb/hr 3.27E-06 4.76E-06 4.85E-06 0.000

lb/mmBtuO2 5.64E-07 8.67E-07 8.29E-07 0.000

mg/dscm 5.75E-04 8.29E-04 7.99E-04 0.001

mg/dscm@7%O2 6.15E-04 9.45E-04 9.03E-04 0.001

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.039 0.0522 0.0343 0.042

Elb/hr 4.11E-05 5.65E-05 3.78E-05 0.000

lb/mmBtuO2 7.10E-06 1.03E-05 6.46E-06 0.000

mg/dscm 7.23E-03 9.84E-03 6.22E-03 0.008

mg/dscm@7%O2 7.73E-03 1.12E-02 7.03E-03 0.009

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.0009 0.0014 0.001112 0.001

Elb/hr 9.49E-07 1.51E-06 1.22E-06 0.000

lb/mmBtuO2 1.64E-07 2.76E-07 2.09E-07 0.000

mg/dscm 1.67E-04 2.64E-04 2.02E-04 0.000

mg/dscm@7%O2 1.79E-04 3.01E-04 2.28E-04 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.0005 0.0007 0.0005 0.001

Elb/hr 5.27E-07 7.57E-07 5.50E-07 0.000

lb/mmBtuO2 9.10E-08 1.38E-07 9.41E-08 0.000

mg/dscm 9.27E-05 1.32E-04 9.07E-05 0.000

mg/dscm@7%O2 9.91E-05 1.50E-04 1.02E-04 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.0108 0.0186 0.0041 0.011

Elb/hr 1.14E-05 2.01E-05 4.51E-06 0.000

lb/mmBtuO2 1.97E-06 3.67E-06 7.72E-07 0.000

mg/dscm 2.00E-03 3.51E-03 7.44E-04 0.002

mg/dscm@7%O2 2.14E-03 4.00E-03 8.41E-04 0.002

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 37.1 50.2 45.4 44.233

Elb/hr 3.91E-02 5.43E-02 5.00E-02 0.048

Wednesday, February 16, 2011 Page 7 of 13
lb/mmBtuO2 6.75E-03 9.89E-03 8.55E-03 0.008

mg/dscm 6.88E+00 9.46E+00 8.24E+00 8.193

mg/dscm@7%O2 7.36E+00 1.08E+01 9.31E+00 9.157

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.0363 0.0457 0.0331 0.038

Elb/hr 3.83E-05 4.94E-05 3.64E-05 0.000

lb/mmBtuO2 6.60E-06 9.01E-06 6.23E-06 0.000

mg/dscm 6.73E-03 8.61E-03 6.01E-03 0.007

mg/dscm@7%O2 7.20E-03 9.81E-03 6.79E-03 0.008

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.0055 0.0075 0.0056 0.006

Elb/hr 5.80E-06 8.11E-06 6.17E-06 0.000

lb/mmBtuO2 1.00E-06 1.48E-06 1.05E-06 0.000

mg/dscm 1.02E-03 1.41E-03 1.02E-03 0.001

mg/dscm@7%O2 1.09E-03 1.61E-03 1.15E-03 0.001

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.0141 0.0222 0.0127 0.016

Elb/hr 1.49E-05 2.40E-05 1.40E-05 0.000

lb/mmBtuO2 2.57E-06 4.37E-06 2.39E-06 0.000

mg/dscm 2.61E-03 4.18E-03 2.30E-03 0.003

mg/dscm@7%O2 2.79E-03 4.76E-03 2.60E-03 0.003

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.461 0.4867 0.4329 0.460

Elb/hr 4.86E-04 5.26E-04 4.77E-04 0.000

lb/mmBtuO2 8.39E-05 9.59E-05 8.15E-05 0.000

mg/dscm 8.55E-02 9.17E-02 7.86E-02 0.085

mg/dscm@7%O2 9.14E-02 1.04E-01 8.88E-02 0.095

Location: Stack Exit - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 31.6 34.5 43.5 36.533

lb/mmBtuO2 8.75E-03 1.03E-02 1.27E-02 0.011

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 11.1 8.6 10.9 10.200

lb/mmBtuO2 3.07E-03 2.58E-03 3.19E-03 0.003

Wednesday, February 16, 2011 Page 8 of 13
Process Run Data

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 92.3 152.8 41.3 95.467

lb/mmBtuO2 2.55E-02 4.58E-02 1.21E-02 0.028

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 5.7 15.6 16.7 12.667

lb/mmBtuO2 1.58E-03 4.67E-03 4.88E-03 0.004

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 129.6 202.9 101.5 144.667

lb/mmBtuO2 3.59E-02 6.08E-02 2.97E-02 0.042

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 118.5 194.3 90.6 134.467

lb/mmBtuO2 3.28E-02 5.82E-02 2.65E-02 0.039

Wednesday, February 16, 2011 Page 9 of 13
Process Run Data

Run Name Value UOM Comments

Target

Value

1 Bituminous Coal Burned 0 Tons/hr 0

1 Average Heat Input 613.5 MMBtu/hr 0

1 Steam Output 570.7 1000 lb steam/hr 0

1 Fuel Oil Firing Rate 0 0

1 Standard Pressure 0 atm 0

1 Standard Temperature 0 Deg F 0

1 Unit Gross Electrical Output 0 MW 0

1 Unit Net Electric Generation 82.6 MWh 0

2 Bituminous Coal Burned 0 Tons/hr 0

2 Average Heat Input 630.8 MMBtu/hr 0

2 Steam Output 569.9 1000 lb steam/hr 0

2 Fuel Oil Firing Rate 0 0

2 Standard Pressure 0 atm 0

2 Standard Temperature 0 Deg F 0

2 Unit Gross Electrical Output 0 MW 0

2 Unit Net Electric Generation 82.1 MWh 0

3 Bituminous Coal Burned 0 Tons/hr 0

3 Average Heat Input 582.5 MMBtu/hr 0

3 Steam Output 539.2 1000 lb steam/hr 0

3 Fuel Oil Firing Rate 0 0

3 Standard Pressure 0 atm 0

3 Standard Temperature 0 Deg F 0

3 Unit Gross Electrical Output 0 MW 0

3 Unit Net Electric Generation 78.2 MWh 0

4 Bituminous Coal Burned 0 Tons/hr 0

4 Average Heat Input 813.5 MMBtu/hr 0

4 Steam Output 570.3 1000 lb steam/hr 0

4 Fuel Oil Firing Rate 0 0

4 Standard Pressure 0 atm 0

4 Standard Temperature 0 Deg F 0

4 Unit Gross Electrical Output 0 MW 0

4 Unit Net Electric Generation 82.7 MWh 0

5 Bituminous Coal Burned 0 Tons/hr 0

Wednesday, February 16, 2011 Page 10 of 13
APCD Run Data

Process Lab Run Data

5 Average Heat Input 828.5 MMBtu/hr 0

5 Steam Output 570.8 1000 lb steam/hr 0

5 Fuel Oil Firing Rate 0 0

5 Standard Pressure 0 atm 0

5 Standard Temperature 0 Deg F 0

5 Unit Gross Electrical Output 0 MW 0

5 Unit Net Electric Generation 82.6 MWh 0

6 Bituminous Coal Burned 0 Tons/hr 0

6 Average Heat Input 813.3 MMBtu/hr 0

6 Steam Output 570.1 1000 lb steam/hr 0

6 Fuel Oil Firing Rate 0 0

6 Standard Pressure 0 atm 0

6 Standard Temperature 0 Deg F 0

6 Unit Gross Electrical Output 0 MW 0

6 Unit Net Electric Generation 82.1 MWh 0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 10635 Btu/lb

1 Fuel Moisture 17.6 %

1 Fuel Mercury Content 8E-06 ppm

1 Fuel Cadmium Content 0 ppm

1 Ultimate/Proximate Analysis 0

1 Fuel Nickel Content 0.003 ppm

1 Fuel Arsenic Content 0.0006 ppm

1 Fuel Chromium Content 0.0008 ppm

1 Fuel Beryllium Content 0.0002 ppm

1 Fuel Lead Content 0.001 ppm

1 Fuel Manganese Content 0.002 ppm

1 Fuel Chlorine Content 0.008 ppm

1 Fuel Fluorine Content 0 ppm

Wednesday, February 16, 2011 Page 11 of 13
Sampling / Stack Data Results Detail

Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 5/11/2010 5/11/2010 5/12/2010

Run Start Time 9:40:00 AM 4:35:00 PM 7:45:00 AM

Run Finish Time 3:55:00 PM 10:50:00 PM 4:10:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 360 360 360

Nozzle Diameter, inches 0.338 0.338 0.338 0.338

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.0087 1.0087 1.0087 1.009

Barometric Pressure, inches of Mercury 29.1 29.1 30.1 29.433

Average Orifice Meter Differential, inches H2O 0.95 1.04 1.05 1.013

Dry Gas Meter Volume Sampled, cubic feet 193.685 194.256 191.905 193.282

Average Dry Gas Meter Temperature, °F 67.89 78.27 69.60 71.920

Dry Gas Meter Volume Sampled, dscf 190.511 187.431 194.649 190.864

Total Moisture Liquid collected, g 406.8 404 345.9 385.567

Volume of Water Vapor, standard cubic feet 19.15 19.02 16.28 18.150

Moisture Content of Stack Gas, % 9.13 9.21 7.72 8.687

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9087 0.9079 0.9228 0.913

Carbon Dioxide, % 11.2 10.4 11.1 10.900

Oxygen, % 7.9 8.7 8.6 8.400

Carbon Monoxide & Nitrogen, % 80.9 80.9 80.3 80.700

Fuel Factor 1.16 1.17 1.11

Dry Molecular Weight, lb/lb-Mole 30.11 30.01 30.12 30.080

Wet Molecular weight, lb/lb-Mole 29.00 28.90 29.18 29.027

Flue Gas Static Pressure, inches of H2O -0.5 -0.5 -0.5 -0.500

Absolute Flue Gas Pressure, inches of Mercury 29.06 29.06 30.06 29.393

Average Stack Gas Temperature, °F 291.63 286.67 261.51 279.937

Average Velocity Head, inches of H2O 0.1134438260

92874

0.114579398

011487

0.116956430

746715

0.115

Average Stack Gas Velocity, feet/second 22.84 22.92 22.27 22.677

Stack Cross-Sectional Area, square feet 1.787 1.787 1.787 1.787

Dry Volumetric Flow Rate, dry scfm 1,518.3 1,532.4 1,620.0 1,556.900

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,448.9 2,457.5 2,387.8 2,431.400

Percent Isokinetic of Sampling Rate, % 100.0 97.4 95.7 97.700

Percent Excess Air, % 58.7 68.7 68.3 65.233

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 18.1 18.1 18.1

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 16, 2011 Page 12 of 13
Location Stack Exit - OTM - 27/28

Average

Run Number 1 2 3

Test Date 5/11/2010 5/11/2010 5/12/2010

Run Start Time 7:45:00 AM 4:35:00 PM 7:45:00 AM

Run Finish Time 3:54:30 PM 10:03:30 PM 3:54:30 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 335.75 344.25 335.25

Nozzle Diameter, inches 0.273 0.273 0.273 0.273

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.014 1.014 1.014 1.014

Barometric Pressure, inches of Mercury 29.1 29.1 29.1 29.100

Average Orifice Meter Differential, inches H2O 0.37 0.37 0.37 0.370

Dry Gas Meter Volume Sampled, cubic feet 126.066 126.834 126.066 126.322

Average Dry Gas Meter Temperature, °F 64.58 76.33 64.58 68.497

Dry Gas Meter Volume Sampled, dscf 125.255 123.257 125.255 124.589

Total Moisture Liquid collected, g 212.6 239.9 218.9 223.800

Volume of Water Vapor, standard cubic feet 10.01 11.29 10.30 10.533

Moisture Content of Stack Gas, % 7.40 8.39 7.60 7.797

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.926 0.9161 0.924 0.922

Carbon Dioxide, % 11.2 10.4 11.1 10.900

Oxygen, % 7.9 8.7 8.6 8.400

Carbon Monoxide & Nitrogen, % 80.9 80.9 80.3 80.700

Fuel Factor 1.16 1.17 1.11

Dry Molecular Weight, lb/lb-Mole 30.11 30.01 30.12 30.080

Wet Molecular weight, lb/lb-Mole 29.21 29.00 29.20 29.137

Flue Gas Static Pressure, inches of H2O -0.5 -0.5 -0.5 -0.500

Absolute Flue Gas Pressure, inches of Mercury 29.06 29.06 29.06 29.060

Average Stack Gas Temperature, °F 262.17 277.83 262.17 267.390

Average Velocity Head, inches of H2O 0.1211670666

19101

0.123120572

305035

0.121167066

619101

0.122

Average Stack Gas Velocity, feet/second 23.06 23.58 23.06 23.233

Stack Cross-Sectional Area, square feet 1.787 1.787 1.787 1.787

Dry Volumetric Flow Rate, dry scfm 1,625.8 1,609.8 1,622.3 1,619.300

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,472.5 2,528.2 2,472.5 2,491.067

Percent Isokinetic of Sampling Rate, % 100.9 97.8 101.2 99.967

Percent Excess Air, % 58.7 68.7 68.3 65.233

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 18.1 18.1 18.1

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 16, 2011 Page 13 of 13