Name: C.D. Holley

Title: Vice President F&H System Operation

Company: Dominion Generation

Sign Date: 8/16/2010

Name: Michael P. Martin

Title: Senior Project Manager

Company: TRC Companies, Inc.

Sign Date: 8/12/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Utility Boiler MACT ICR - Possum Point Power Station Unit 5

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, January 13, 2011 Page 1 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Facility Information:

Possum Point

19000 Possum Point Road

Dumfries VA 22026

Contact: David Nuckols

Phone: 804-796-6021

Fax: 804-796-6004

Email: david.nuckols@dom.com

Testing Company:

TRC Companies, Inc.

650 Suffolk Street

Lowell MA 01854

Contact:Michael P. Martin

Phone: 978-656-3550

Fax: 978-453-4215

Email: mmartin@trcsolutions.com

Air Permit Number:

3804

Permitted Source ID/Name:

5

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Unit 5 is an 8500 mmBtu/hr tangentially fired oil boiler w/ multicyclone.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 5115300002 FRS #: 110000340774

SCC / Description 10100404 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Tangential Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 288 0 0 0 1320 1788 4 6

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit Carbon Monoxide Method 10 3 120 0

Stack Exit Formaldehyde Method 0011 3 120 0

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Thursday, January 13, 2011 Page 2 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Other TCDD Method 23 0

Stack Exit Other PeCDD Method 23 0

Stack Exit Other HxCDD Method 23 0

Stack Exit Other HpCDD Method 23 0

Stack Exit Other TCDF Method 23 0

Stack Exit Other PeCDF Method 23 0

Stack Exit Other HxCDF Method 23 0

Stack Exit Other HpCDF Method 23 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Method 25A 3 120 0 NMHC emissions 

only. Methane 

emissions reported in 

excel template.

Stack Exit

Stack Exit Hydrogen Chloride Method 26A 3 60 0

Stack Exit Hydrogen Fluoride Method 26A 3 60 0

Stack Exit Filterable PM2.5 OTM - 27/28 3 180 0

Stack Exit Filterable Particulate OTM - 27/28 3 180 0

Stack Exit Total Particulate OTM - 27/28 3 180 0

Organic Condensible 

Particulate

Stack Exit OTM - 27/28 3 180 0

Inorganic (Aqueous) 

Condensible Part.

Stack Exit OTM - 27/28 3 180 0

Stack Exit Total PM2.5 OTM - 27/28 3 180 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Thursday, January 13, 2011 Page 3 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Stack Exit Selenium Method 29 3 240 0

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Cobalt Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Sulfur Dioxide Method 6C 3 120 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 120 0

Thursday, January 13, 2011 Page 4 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Sampling / Stack Data Results Summary

Location Stack Exit - Method 0011

Average

Run Number 1 2 3

Test Date 6/8/2010 6/9/2010 6/9/2010

Run Start Time

Run Finish Time

Net Run Time, minutes 120 120 120

Dry Gas Meter Volume Sampled, dscf 92.073 92.662 92.646 92.460

Moisture Content of Stack Gas, % 6.41 6.29 5.75 6.150

Moisture Saturation at Stack Gas Temperature, % 84.90 87.01 86.21 86.040

Carbon Dioxide, % 7.876 7.912 7.912 7.900

Oxygen, % 11.223 11.259 11.259 11.247

Average Stack Gas Temperature, °F 203.63 204.83 204.38 204.280

Dry Volumetric Flow Rate, dry scfm 1,219,680.2 1,240,740.2 1,248,532.9 1,236,317.76

7

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,646,786.4 1,676,101.2 1,675,829.8 1,666,239.13

3

Percent Isokinetic of Sampling Rate, % 99.5 98.4 97.8 98.567

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, January 13, 2011 Page 5 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 10 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 23

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, January 13, 2011 Page 6 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 25A 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, January 13, 2011 Page 7 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, January 13, 2011 Page 8 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 6C 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, January 13, 2011 Page 9 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 7E 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, January 13, 2011 Page 10 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, January 13, 2011 Page 11 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Emissions Summary

Location: Stack Exit - Method 0011

Compound: Formaldehyde

Average

RunNumber 1 2 3

Mass_mg 0.0182 0.0297 0.0176 0.022

lb/mmBtuO2 8.65E-06 1.41E-05 8.34E-06 0.000

ppm 5.59E-03 9.07E-03 5.37E-03 0.007

ppm@7%O2 8.03E-03 1.31E-02 7.74E-03 0.010

Location: Stack Exit - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ppm 0.00E+00 0.00E+00 0.00E+00 0.000

ppm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Location: Stack Exit - Method 10 3

Compound: Carbon Monoxide

Average

Run 4

lb/mmBtuO2 -2.17E-05 0.000

ppm -1.50E-02 -0.015

ppm@7%O2 -2.16E-02 -0.022

Location: Stack Exit - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000859 0.0000000108 0.0000000044 0.000

lb/mmBtuO2 9.84E-13 1.26E-12 5.19E-13 0.000

ng/dscm 7.96E-04 1.03E-03 4.20E-04 0.001

ng/dscm@7%O2 1.14E-03 1.46E-03 6.02E-04 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000037 0.0000000036 0.0000000031 0.000

lb/mmBtuO2 4.24E-13 4.19E-13 3.65E-13 0.000

ng/dscm 3.43E-04 3.43E-04 2.96E-04 0.000

ng/dscm@7%O2 4.92E-04 4.87E-04 4.24E-04 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000046 0.0000000044 0.0000000037 0.000

lb/mmBtuO2 5.27E-13 5.12E-13 4.36E-13 0.000

ng/dscm 4.26E-04 4.19E-04 3.53E-04 0.000

ng/dscm@7%O2 6.10E-04 5.94E-04 5.06E-04 0.001

Thursday, January 13, 2011 Page 12 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000008 0.0000000055 0.0000000054 0.000

lb/mmBtuO2 9.17E-13 6.41E-13 6.37E-13 0.000

ng/dscm 7.42E-04 5.24E-04 5.15E-04 0.001

ng/dscm@7%O2 1.06E-03 7.43E-04 7.38E-04 0.001

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000004 0.0000000026 0.0000000038 0.000

lb/mmBtuO2 4.58E-13 3.03E-13 4.48E-13 0.000

ng/dscm 3.71E-04 2.48E-04 3.62E-04 0.000

ng/dscm@7%O2 5.32E-04 3.52E-04 5.19E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000084 0.0000000058 0.0000000057 0.000

lb/mmBtuO2 9.63E-13 6.76E-13 6.72E-13 0.000

ng/dscm 7.79E-04 5.52E-04 5.44E-04 0.001

ng/dscm@7%O2 1.12E-03 7.83E-04 7.80E-04 0.001

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000037 0.0000000024 0.0000000034 0.000

lb/mmBtuO2 4.24E-13 2.80E-13 4.01E-13 0.000

ng/dscm 3.43E-04 2.28E-04 3.24E-04 0.000

ng/dscm@7%O2 4.92E-04 3.23E-04 4.64E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000081 0.0000000056 0.0000000055 0.000

lb/mmBtuO2 9.28E-13 6.52E-13 6.48E-13 0.000

ng/dscm 7.51E-04 5.33E-04 5.25E-04 0.001

ng/dscm@7%O2 1.08E-03 7.56E-04 7.52E-04 0.001

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000042 0.0000000027 0.0000000039 0.000

lb/mmBtuO2 4.81E-13 3.14E-13 4.60E-13 0.000

ng/dscm 3.89E-04 2.57E-04 3.72E-04 0.000

ng/dscm@7%O2 5.57E-04 3.65E-04 5.33E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000055 0.0000000063 0.0000000052 0.000

lb/mmBtuO2 6.30E-13 7.34E-13 6.13E-13 0.000

Thursday, January 13, 2011 Page 13 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

ng/dscm 5.10E-04 6.00E-04 4.96E-04 0.001

ng/dscm@7%O2 7.31E-04 8.51E-04 7.11E-04 0.001

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000073 0.0000000018 0.0000000018 0.000

lb/mmBtuO2 8.37E-13 2.10E-13 2.12E-13 0.000

ng/dscm 6.77E-04 1.71E-04 1.72E-04 0.000

ng/dscm@7%O2 9.70E-04 2.43E-04 2.46E-04 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.0000000046 0.0000000029 0.0000000024 0.000

lb/mmBtuO2 5.27E-13 3.38E-13 2.83E-13 0.000

ng/dscm 4.26E-04 2.76E-04 2.29E-04 0.000

ng/dscm@7%O2 6.10E-04 3.91E-04 3.28E-04 0.000

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.00000006 0.0000000573 0.0000000386 0.000

lb/mmBtuO2 6.88E-12 6.67E-12 4.55E-12 0.000

ng/dscm 5.56E-03 5.46E-03 3.68E-03 0.005

ng/dscm@7%O2 7.97E-03 7.74E-03 5.27E-03 0.007

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.000000301 0.000000268 0.000000232 0.000

lb/mmBtuO2 3.45E-11 3.12E-11 2.74E-11 0.000

ng/dscm 2.79E-02 2.55E-02 2.21E-02 0.025

ng/dscm@7%O2 4.00E-02 3.62E-02 3.17E-02 0.036

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.0000000279 0.000000023 0.0000000184 0.000

lb/mmBtuO2 3.20E-12 2.68E-12 2.17E-12 0.000

ng/dscm 2.59E-03 2.19E-03 1.76E-03 0.002

ng/dscm@7%O2 3.71E-03 3.11E-03 2.52E-03 0.003

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.0000000212 0.0000000212 0.0000000188 0.000

lb/mmBtuO2 2.43E-12 2.47E-12 2.22E-12 0.000

ng/dscm 1.97E-03 2.02E-03 1.79E-03 0.002

ng/dscm@7%O2 2.82E-03 2.87E-03 2.57E-03 0.003

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Thursday, January 13, 2011 Page 14 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Mass_mg 0.000000841 0.000000614 0.000000614 0.000

lb/mmBtuO2 9.64E-11 7.15E-11 7.24E-11 0.000

ng/dscm 7.80E-02 5.85E-02 5.86E-02 0.065

ng/dscm@7%O2 1.12E-01 8.30E-02 8.40E-02 0.093

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.000000015 0.0000000141 0.000000013 0.000

lb/mmBtuO2 1.72E-12 1.64E-12 1.53E-12 0.000

ng/dscm 1.39E-03 1.34E-03 1.24E-03 0.001

ng/dscm@7%O2 1.99E-03 1.90E-03 1.78E-03 0.002

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000039 0.0000000025 0.0000000036 0.000

lb/mmBtuO2 4.47E-13 2.91E-13 4.24E-13 0.000

ng/dscm 3.62E-04 2.38E-04 3.43E-04 0.000

ng/dscm@7%O2 5.19E-04 3.38E-04 4.92E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000068 0.0000000017 0.0000000016 0.000

lb/mmBtuO2 7.79E-13 1.98E-13 1.89E-13 0.000

ng/dscm 6.30E-04 1.62E-04 1.53E-04 0.000

ng/dscm@7%O2 9.03E-04 2.30E-04 2.19E-04 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000088 0.000000006 0.0000000076 0.000

lb/mmBtuO2 1.01E-12 6.99E-13 8.96E-13 0.000

ng/dscm 8.16E-04 5.71E-04 7.25E-04 0.001

ng/dscm@7%O2 1.17E-03 8.10E-04 1.04E-03 0.001

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000075 0.0000000062 0.0000000056 0.000

lb/mmBtuO2 8.59E-13 7.22E-13 6.60E-13 0.000

ng/dscm 6.95E-04 5.90E-04 5.34E-04 0.001

ng/dscm@7%O2 9.96E-04 8.37E-04 7.65E-04 0.001

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.0000000024 0.0000000027 0.000

lb/mmBtuO2 3.67E-13 2.80E-13 3.18E-13 0.000

ng/dscm 2.97E-04 2.28E-04 2.58E-04 0.000

ng/dscm@7%O2 4.26E-04 3.23E-04 3.70E-04 0.000

Thursday, January 13, 2011 Page 15 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.000000013 0.000000012 0.000000012 0.000

lb/mmBtuO2 1.49E-12 1.40E-12 1.41E-12 0.000

ng/dscm 1.21E-03 1.14E-03 1.14E-03 0.001

ng/dscm@7%O2 1.73E-03 1.62E-03 1.63E-03 0.002

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.000000195 0.000000164 0.000000204 0.000

lb/mmBtuO2 2.23E-11 1.91E-11 2.41E-11 0.000

ng/dscm 1.81E-02 1.56E-02 1.95E-02 0.018

ng/dscm@7%O2 2.59E-02 2.21E-02 2.79E-02 0.025

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.00000000867 0.00000000716 0.00000000817 0.000

lb/mmBtuO2 9.94E-13 8.34E-13 9.63E-13 0.000

ng/dscm 8.04E-04 6.82E-04 7.79E-04 0.001

ng/dscm@7%O2 1.15E-03 9.67E-04 1.12E-03 0.001

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000448 0.0000000677 0.000000018 0.000

lb/mmBtuO2 5.13E-12 7.88E-12 2.12E-12 0.000

ng/dscm 4.15E-03 6.45E-03 1.72E-03 0.004

ng/dscm@7%O2 5.95E-03 9.15E-03 2.46E-03 0.006

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000027 0.000000011 0.000000011 0.000

lb/mmBtuO2 3.09E-12 1.28E-12 1.30E-12 0.000

ng/dscm 2.50E-03 1.05E-03 1.05E-03 0.002

ng/dscm@7%O2 3.58E-03 1.49E-03 1.50E-03 0.002

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000851 0.0000000102 0.00000000583 0.000

lb/mmBtuO2 9.75E-13 1.19E-12 6.87E-13 0.000

ng/dscm 7.89E-04 9.71E-04 5.56E-04 0.001

ng/dscm@7%O2 1.13E-03 1.38E-03 7.97E-04 0.001

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

Thursday, January 13, 2011 Page 16 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0 0.00000000325 0 0.000

lb/mmBtuO2 0.00E+00 3.79E-13 0.00E+00 0.000

ng/dscm 0.00E+00 3.09E-04 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 4.38E-04 0.00E+00 0.000

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total Dioxins

Average

RunNumber 1 2 3

Thursday, January 13, 2011 Page 17 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Mass_mg 0.0000001007 0.0000001179 0.00000005763 0.000

lb/mmBtuO2 1.15E-11 1.37E-11 6.79E-12 0.000

ng/dscm 9.34E-03 1.12E-02 5.50E-03 0.009

ng/dscm@7%O2 1.34E-02 1.59E-02 7.88E-03 0.012

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0.0000000727 0.00000004215 0.0000000415 0.000

lb/mmBtuO2 8.33E-12 4.91E-12 4.89E-12 0.000

ng/dscm 6.74E-03 4.01E-03 3.96E-03 0.005

ng/dscm@7%O2 9.66E-03 5.69E-03 5.67E-03 0.007

Location: Stack Exit - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 -3.73E-04 0.00E+00 0.00E+00 0.000

ppm -1.63E-01 0.00E+00 0.00E+00 -0.054

ppm@7%O2 -2.36E-01 0.00E+00 0.00E+00 -0.079

Location: Stack Exit - Method 25A 3

Compound: Total organic compounds (TOC) as 

Average

Run 4

lb/mmBtuO2 0.00E+00 0.000

ppm 0.00E+00 0.000

ppm@7%O2 0.00E+00 0.000

Location: Stack Exit - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.73 0.691 0.653 0.691

lb/mmBtuO2 6.83E-04 6.65E-04 6.29E-04 0.001

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.419 0.397 0.375 0.397

lb/mmBtuO2 3.92E-04 3.82E-04 3.61E-04 0.000

Location: Stack Exit - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.0806 0.226257 0.20083 0.169

lb/mmBtuO2 2.02E-05 5.67E-05 5.17E-05 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Thursday, January 13, 2011 Page 18 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Mass_mg 0.00681 0.013421 0.010931 0.010

lb/mmBtuO2 1.71E-06 3.36E-06 2.81E-06 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.000516 0.00116 0.001061 0.001

lb/mmBtuO2 1.29E-07 2.91E-07 2.73E-07 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00066 0.00103 0.000986 0.001

lb/mmBtuO2 1.65E-07 2.58E-07 2.54E-07 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.04439 0.04463 0.06006 0.050

lb/mmBtuO2 1.11E-05 1.12E-05 1.55E-05 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.0806 0.155301 0.129493 0.122

lb/mmBtuO2 2.02E-05 3.89E-05 3.33E-05 0.000

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.0627 0.146337 0.120492 0.110

lb/mmBtuO2 1.57E-05 3.67E-05 3.10E-05 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.0905 0.14324 0.11241 0.115

lb/mmBtuO2 2.27E-05 3.59E-05 2.89E-05 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 2.027 4.419 3.7868 3.411

lb/mmBtuO2 5.08E-04 1.11E-03 9.75E-04 0.001

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.00488 0.00581 0.00418 0.005

lb/mmBtuO2 1.22E-06 1.46E-06 1.08E-06 0.000

Location: Stack Exit - Method 6C

Thursday, January 13, 2011 Page 19 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 7.01E-01 6.99E-01 6.98E-01 0.699

ppm 2.11E+02 2.11E+02 2.12E+02 211.333

ppm@7%O2 3.06E+02 3.04E+02 3.04E+02 304.667

Location: Stack Exit - Method 6C 3

Compound: Sulfur Dioxide

Average

Run 4

lb/mmBtuO2 7.02E-01 0.702

ppm 2.13E+02 213.000

ppm@7%O2 3.06E+02 306.000

Location: Stack Exit - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 2.30E-01 2.29E-01 2.19E-01 0.226

ppm 9.64E+01 9.61E+01 9.27E+01 95.067

ppm@7%O2 1.40E+02 1.39E+02 1.33E+02 137.333

Location: Stack Exit - Method 7E 3

Compound: Nitrogen oxides (NOx)

Average

Run 4

lb/mmBtuO2 2.18E-01 0.218

ppm 9.18E+01 91.800

ppm@7%O2 1.32E+02 132.000

Location: Stack Exit - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 3 4 5

Mass_mg 84.5 67.3 52.9 68.233

lb/mmBtuO2 7.22E-02 5.42E-02 4.30E-02 0.056

Compound: Filterable PM2.5

Average

RunNumber 3 4 5

Mass_mg 43.8 43.9 42 43.233

lb/mmBtuO2 3.74E-02 3.54E-02 3.41E-02 0.036

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 3 4 5

Mass_mg 47.27 8.17 19.97 25.137

lb/mmBtuO2 4.04E-02 6.58E-03 1.62E-02 0.021

Thursday, January 13, 2011 Page 20 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Process Run Data

Compound: Organic Condensible Particulate

Average

RunNumber 3 4 5

Mass_mg 7.83 3.03 10.33 7.063

lb/mmBtuO2 6.69E-03 2.44E-03 8.40E-03 0.006

Compound: Total Particulate

Average

RunNumber 3 4 5

Mass_mg 139.6 78.5 83.2 100.433

lb/mmBtuO2 1.19E-01 6.32E-02 6.76E-02 0.083

Compound: Total PM2.5

Average

RunNumber 3 4 5

Mass_mg 98.9 55.1 72.3 75.433

lb/mmBtuO2 8.45E-02 4.44E-02 5.88E-02 0.063

Thursday, January 13, 2011 Page 21 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input 3812.5 Million Btus/hr Collected during 

M29 run 1

0

10 Heat Input 3839.5 Million Btus/hr Collected during 

OTM 27/28 run 5

0

11 Heat Input 3816.4 Million Btus/hr Collected during 

M0011 run 1

0

12 Heat Input 3817.1 Million Btus/hr Collected during 

M0011 run 2

0

13 Heat Input 3818.8 Million Btus/hr Collected during 

M0011 run 3

0

14 Heat Input 3816 Million Btus/hr Collected during 

M23 run 1

0

15 Heat Input 3851.8 Million Btus/hr Collected during 

M23 run 2

0

16 Heat Input 3861.2 Million Btus/hr Collected during 

M23 run 3

0

17 Heat Input 3851.3 Million Btus/hr Collected during 

M26A run 1

0

18 Heat Input 3847.1 Million Btus/hr Collected during 

M26A run 2

0

2 Heat Input 3830 Million Btus/hr Collected during 

M29 run 2

0

3 Heat Input 3817.8 Million Btus/hr Collected during 

M29 run 3

0

4 Heat Input 3836.2 Million Btus/hr Collected during 

run 1 of Method 

6C, 7E, 10, and 

25A

0

5 Heat Input 3826.5 Million Btus/hr Collected during 

run 2 of Method 

6C, 7E, 10, and 

25A

0

6 Heat Input 3819.9 Million Btus/hr Collected during 

run 3 of Method 

6C, 7E, 10, and 

25A

0

7 Heat Input 3814.7 Million Btus/hr Collected during 

run 4 of Method 

6C, 7E, 10, and 

25A

0

8 Heat Input 3826.5 Million Btus/hr Collected during 

OTM 27/28 run 3

0

9 Heat Input 3817.3 Million Btus/hr Collected during 

OTM 27/28 run 4

0

Thursday, January 13, 2011 Page 22 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

1 Avg. Heat Input 63.542 MMBtu/min Collected during 

M29 run 1

0

10 Avg. Heat Input 63.991 MMBtu/min Collected during 

OTM 27/28 run 5

0

11 Avg. Heat Input 63.606 MMBtu/min Collected during 

M0011 run 1

0

12 Avg. Heat Input 63.619 MMBtu/min Collected during 

M0011 run 2

0

13 Avg. Heat Input 63.647 MMBtu/min Collected during 

M0011 run 3

0

14 Avg. Heat Input 63.6 MMBtu/min Collected during 

M23 run 1

0

15 Avg. Heat Input 64.196 MMBtu/min Collected during 

M23 run 2

0

16 Avg. Heat Input 64.353 MMBtu/min Collected during 

M23 run 3

0

17 Avg. Heat Input 64.188 MMBtu/min Collected during 

M26A run 1

0

18 Avg. Heat Input 64.118 MMBtu/min Collected during 

M26A run 2

0

2 Avg. Heat Input 63.833 MMBtu/min Collected during 

M29 run 2

0

3 Avg. Heat Input 63.63 MMBtu/min Collected during 

M29 run 3

0

4 Avg. Heat Input 63.936 MMBtu/min Collected during 

run 1 of Method 

6C, 7E, 10, and 

25A

0

5 Avg. Heat Input 63.775 MMBtu/min Collected during 

run 2 of Method 

6C, 7E, 10, and 

25A

0

6 Avg. Heat Input 63.664 MMBtu/min Collected during 

run 3 of Method 

6C, 7E, 10, and 

25A

0

7 Avg. Heat Input 63.578 MMBtu/min Collected during 

run 4 of Method 

6C, 7E, 10, and 

25A

0

8 Avg. Heat Input 63.775 MMBtu/min Collected during 

OTM 27/28 run 3

0

9 Avg. Heat Input 63.621 MMBtu/min Collected during 

OTM 27/28 run 4

0

1 Combined Total Fuel Flow 417.29 gpm Collected during 

M29 run 1

0

Thursday, January 13, 2011 Page 23 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

10 Combined Total Fuel Flow 420.24 gpm Collected during 

OTM 27/28 run 5

0

11 Combined Total Fuel Flow 417.71 gpm Collected during 

M0011 run 1

0

12 Combined Total Fuel Flow 417.8 gpm Collected during 

M0011 run 2

0

13 Combined Total Fuel Flow 417.98 gpm Collected during 

M0011 run 3

0

14 Combined Total Fuel Flow 417.67 gpm Collected during 

M23 run 1

0

15 Combined Total Fuel Flow 421.59 gpm Collected during 

M23 run 2

0

16 Combined Total Fuel Flow 422.61 gpm Collected during 

M23 run 3

0

17 Combined Total Fuel Flow 421.54 gpm Collected during 

M26A run 1

0

18 Combined Total Fuel Flow 421.07 gpm Collected during 

M26A run 2

0

2 Combined Total Fuel Flow 419.2 gpm Collected during 

M29 run 2

0

3 Combined Total Fuel Flow 417.87 gpm Collected during 

M29 run 3

0

4 Combined Total Fuel Flow 419.88 gpm Collected during 

run 1 of Method 

6C, 7E, 10, and 

25A

0

5 Combined Total Fuel Flow 418.82 gpm Collected during 

run 2 of Method 

6C, 7E, 10, and 

25A

0

6 Combined Total Fuel Flow 418.09 gpm Collected during 

run 3 of Method 

6C, 7E, 10, and 

25A

0

7 Combined Total Fuel Flow 417.53 gpm Collected during 

run 4 of Method 

6C, 7E, 10, and 

25A

0

8 Combined Total Fuel Flow 418.82 gpm Collected during 

OTM 27/28 run 3

0

9 Combined Total Fuel Flow 417.81 gpm Collected during 

OTM 27/28 run 4

0

1 Unit Gross Electrical Output 356.23 MW Collected during 

M29 run 1

0

10 Unit Gross Electrical Output 347.90 MW Collected during 

OTM 27/28 run 5

0

Thursday, January 13, 2011 Page 24 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

11 Unit Gross Electrical Output 351.51 MW Collected during 

M0011 run 1

0

12 Unit Gross Electrical Output 351.63 MW Collected during 

M0011 run 2

0

13 Unit Gross Electrical Output 351.55 MW Collected during 

M0011 run 3

0

14 Unit Gross Electrical Output 349.54 MW Collected during 

M23 run 1

0

15 Unit Gross Electrical Output 349.27 MW Collected during 

M23 run 2

0

16 Unit Gross Electrical Output 353.13 MW Collected during 

M23 run 3

0

17 Unit Gross Electrical Output 348.72 MW Collected during 

M26A run 1

0

18 Unit Gross Electrical Output 350.22 MW Collected during 

M26A run 2

0

2 Unit Gross Electrical Output 355.36 MW Collected during 

M29 run 2

0

3 Unit Gross Electrical Output 351.6 MW Collected during 

M29 run 3

0

4 Unit Gross Electrical Output 356.34 MW Collected during 

run 1 of Method 

6C, 7E, 10, and 

25A

0

5 Unit Gross Electrical Output 353.44 MW Collected during 

run 2 of Method 

6C, 7E, 10, and 

25A

0

6 Unit Gross Electrical Output 351.67 MW Collected during 

run 3 of Method 

6C, 7E, 10, and 

25A

0

7 Unit Gross Electrical Output 351.5 MW Collected during 

run 4 of Method 

6C, 7E, 10, and 

25A

0

8 Unit Gross Electrical Output 353.44 MW Collected during 

OTM 27/28 run 3

0

9 Unit Gross Electrical Output 349.02 MW Collected during 

OTM 27/28 run 4

0

1 Unit Net Electric Generation 324.29 MW Collected during 

M29 run 1

0

10 Unit Net Electric Generation 316.17 MW Collected during 

OTM 27/28 run 5

0

11 Unit Net Electric Generation 319.53 MW Collected during 

M0011 run 1

0

Thursday, January 13, 2011 Page 25 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

12 Unit Net Electric Generation 319.71 MW Collected during 

M0011 run 2

0

13 Unit Net Electric Generation 319.65 MW Collected during 

M0011 run 3

0

14 Unit Net Electric Generation 317.70 MW Collected during 

M23 run 1

0

15 Unit Net Electric Generation 317.52 MW Collected during 

M23 run 2

0

16 Unit Net Electric Generation 321.37 MW Collected during 

M23 run 3

0

17 Unit Net Electric Generation 316.93 MW Collected during 

M26A run 1

0

18 Unit Net Electric Generation 318.46 MW Collected during 

M26A run 2

0

2 Unit Net Electric Generation 323.53 MW Collected during 

M29 run 2

0

3 Unit Net Electric Generation 319.65 MW Collected during 

M29 run 3

0

4 Unit Net Electric Generation 324.49 MW Collected during 

run 1 of Method 

6C, 7E, 10, and 

25A

0

5 Unit Net Electric Generation 321.61 MW Collected during 

run 2 of Method 

6C, 7E, 10, and 

25A

0

6 Unit Net Electric Generation 319.74 MW Collected during 

run 3 of Method 

6C, 7E, 10, and 

25A

0

7 Unit Net Electric Generation 319.52 MW Collected during 

run 4 of Method 

6C, 7E, 10, and 

25A

0

8 Unit Net Electric Generation 321.61 MW Collected during 

OTM 27/28 run 3

0

9 Unit Net Electric Generation 317.19 MW Collected during 

OTM 27/28 run 4

0

1 Steam Output 2276 1000 lbs steam/hr Collected during 

M29 run 1

0

10 Steam Output 2173.41000 lbs steam/hr Collected during 

OTM 27/28 run 5

0

11 Steam Output 2222.31000 lbs steam/hr Collected during 

M0011 run 1

0

12 Steam Output 2202.31000 lbs steam/hr Collected during 

M0011 run 2

0

Thursday, January 13, 2011 Page 26 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

13 Steam Output 2186.81000 lbs steam/hr Collected during 

M0011 run 3

0

14 Steam Output 2155.81000 lbs steam/hr Collected during 

M23 run 1

0

15 Steam Output 2178.71000 lbs steam/hr Collected during 

M23 run 2

0

16 Steam Output 2124.01000 lbs steam/hr Collected during 

M23 run 3

0

17 Steam Output 2195.41000 lbs steam/hr Collected during 

M26A run 1

0

18 Steam Output 2151.61000 lbs steam/hr Collected during 

M26A run 2

0

2 Steam Output 2263.11000 lbs steam/hr Collected during 

M29 run 2

0

3 Steam Output 2225.91000 lbs steam/hr Collected during 

M29 run 3

0

4 Steam Output 2269.01000 lbs steam/hr Collected during 

run 1 of Method 

6C, 7E, 10, and 

25A

0

5 Steam Output 2254.31000 lbs steam/hr Collected during 

run 2 of Method 

6C, 7E, 10, and 

25A

0

6 Steam Output 2233 1000 lbs steam/hr Collected during 

run 3 of Method 

6C, 7E, 10, and 

25A

0

7 Steam Output 2215.21000 lbs steam/hr Collected during 

run 4 of Method 

6C, 7E, 10, and 

25A

0

8 Steam Output 2254.31000 lbs steam/hr Collected during 

OTM 27/28 run 3

0

9 Steam Output 2145.41000 lbs steam/hr Collected during 

OTM 27/28 run 4

0

1 Fuel Flow Furnace B 205.1 gpm Collected during 

M29 run 1

0

10 Fuel Flow Furnace B 205.92 gpm Collected during 

OTM 27/28 run 5

0

11 Fuel Flow Furnace B 204.33 gpm Collected during 

M0011 run 1

0

12 Fuel Flow Furnace B 205.03 gpm Collected during 

M0011 run 2

0

13 Fuel Flow Furnace B 205.22 gpm Collected during 

M0011 run 3

0

Thursday, January 13, 2011 Page 27 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

14 Fuel Flow Furnace B 204.74 gpm Collected during 

M23 run 1

0

15 Fuel Flow Furnace B 206.79 gpm Collected during 

M23 run 2

0

16 Fuel Flow Furnace B 207.89 gpm Collected during 

M23 run 3

0

17 Fuel Flow Furnace B 206.86 gpm Collected during 

M26A run 1

0

18 Fuel Flow Furnace B 206.48 gpm Collected during 

M26A run 2

0

2 Fuel Flow Furnace B 206.20 gpm Collected during 

M29 run 2

0

3 Fuel Flow Furnace B 204.53 gpm Collected during 

M29 run 3

0

4 Fuel Flow Furnace B 206.75 gpm Collected during 

run 1 of Method 

6C, 7E, 10, and 

25A

0

5 Fuel Flow Furnace B 205.74 gpm Collected during 

run 2 of Method 

6C, 7E, 10, and 

25A

0

6 Fuel Flow Furnace B 204.77 gpm Collected during 

run 3 of Method 

6C, 7E, 10, and 

25A

0

7 Fuel Flow Furnace B 204.16 gpm Collected during 

run 4 of Method 

6C, 7E, 10, and 

25A

0

8 Fuel Flow Furnace B 205.74 gpm Collected during 

OTM 27/28 run 3

0

9 Fuel Flow Furnace B 204.77 gpm Collected during 

OTM 27/28 run 4

0

1 Fuel Flow Furnace A 212.2 gpm Collected during 

M29 run 1

0

10 Fuel Flow Furnace A 214.32 gpm Collected during 

OTM 27/28 run 5

0

11 Fuel Flow Furnace A 213.38 gpm Collected during 

M0011 run 1

0

12 Fuel Flow Furnace A 212.77 gpm Collected during 

M0011 run 2

0

13 Fuel Flow Furnace A 212.76 gpm Collected during 

M0011 run 3

0

14 Fuel Flow Furnace A 212.93 gpm Collected during 

M23 run 1

0

Thursday, January 13, 2011 Page 28 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

15 Fuel Flow Furnace A 214.79 gpm Collected during 

M23 run 2

0

16 Fuel Flow Furnace A 214.73 gpm Collected during 

M23 run 3

0

17 Fuel Flow Furnace A 214.68 gpm Collected during 

M26A run 1

0

18 Fuel Flow Furnace A 214.6 gpm Collected during 

M26A run 2

0

2 Fuel Flow Furnace A 213 gpm Collected during 

M29 run 2

0

3 Fuel Flow Furnace A 213.34 gpm Collected during 

M29 run 3

0

4 Fuel Flow Furnace A 213.13 gpm Collected during 

run 1 of Method 

6C, 7E, 10, and 

25A

0

5 Fuel Flow Furnace A 213.08 gpm Collected during 

run 2 of Method 

6C, 7E, 10, and 

25A

0

6 Fuel Flow Furnace A 213.32 gpm Collected during 

run 3 of Method 

6C, 7E, 10, and 

25A

0

7 Fuel Flow Furnace A 213.37 gpm Collected during 

run 4 of Method 

6C, 7E, 10, and 

25A

0

8 Fuel Flow Furnace A 213.08 gpm Collected during 

OTM 27/28 run 3

0

9 Fuel Flow Furnace A 213.04 gpm Collected during 

OTM 27/28 run 4

0

1 Heavy Oil HHV 152273 Btu/lb Collected during 

M29 run 1

0

2 Heavy Oil HHV 152273 Btu/lb Collected during 

M29 run 2

0

3 Heavy Oil HHV 152273 Btu/lb Collected during 

M29 run 3

0

4 Heavy Oil HHV 152273 Btu/lb Collected during 

run 1 of Method 

6C, 7E, 10, and 

25A

0

5 Heavy Oil HHV 152273 Btu/lb Collected during 

run 2 of Method 

6C, 7E, 10, and 

25A

0

Thursday, January 13, 2011 Page 29 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

6 Heavy Oil HHV 152273 Btu/lb Collected during 

run 3 of Method 

6C, 7E, 10, and 

25A

0

7 Heavy Oil HHV 152273 Btu/lb Collected during 

run 4 of Method 

6C, 7E, 10, and 

25A

0

8 Heavy Oil HHV 152273 Btu/lb Collected during 

OTM 27/28 run 3

0

9 Heavy Oil HHV 152273 Btu/lb Collected during 

OTM 27/28 run 4

0

10 Heavy Oil HHV 152273 Btu/lb Collected during 

OTM 27/28 run 5

0

11 Heavy Oil HHV 152273 Btu/lb Collected during 

M0011 run 1

0

12 Heavy Oil HHV 152273 Btu/lb Collected during 

M0011 run 2

0

13 Heavy Oil HHV 152273 Btu/lb Collected during 

M0011 run 3

0

14 Heavy Oil HHV 152273 Btu/lb Collected during 

M23 run 1

0

15 Heavy Oil HHV 152273 Btu/lb Collected during 

M23 run 2

0

16 Heavy Oil HHV 152273 Btu/lb Collected during 

M23 run 3

0

17 Heavy Oil HHV 152273 Btu/lb Collected during 

M26A run 1

0

18 Heavy Oil HHV 152273 Btu/lb Collected during 

M26A run 2

0

19 Heat Input 3853.5 Million Btus/hr Collected during 

M26A run 3

0

19 Avg. Heat Input 64.225 MMBtu/min Collected during 

M26A run 3

0

19 Combined Total Fuel Flow 421.77 gpm Collected during 

M26A run 3

0

19 Unit Gross Electrical Output 352.03 MW Collected during 

M26A run 3

0

19 Unit Net Electric Generation 320.24 MW Collected during 

M26A run 3

0

19 Steam Output 2114.21000 lbs steam/hr Collected during 

M26A run 3

0

19 Fuel Flow Furnace B 207.39 gpm Collected during 

M26A run 3

0

19 Fuel Flow Furnace A 214.39 gpm Collected during 

M26A run 3

0

Thursday, January 13, 2011 Page 30 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

APCD Run Data

Process Lab Run Data

19 Heavy Oil HHV 152273 Btu/lb Collected during 

M26A run 3

0

Run Name Value UOM Comments

Target

Value

1 MULTIPLE CYCLONES 0

Thursday, January 13, 2011 Page 31 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Sampling / Stack Data Results Detail

Location Stack Exit - Method 0011

Average

Run Number 1 2 3

Test Date 6/8/2010 6/9/2010 6/9/2010

Run Start Time

Run Finish Time

Net Traversing Points 24 24 24

Net Run Time, minutes 120 120 120

Nozzle Diameter, inches 0.229 0.229 0.229 0.229

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9942 0.9942 0.9942 0.994

Barometric Pressure, inches of Mercury 29.8 29.8 29.8 29.800

Average Orifice Meter Differential, inches H2O 2.00 2.08 2.09 2.057

Dry Gas Meter Volume Sampled, cubic feet 94.636 94.793 94.540 94.656

Average Dry Gas Meter Temperature, °F 80.04 77.60 76.27 77.970

Dry Gas Meter Volume Sampled, dscf 92.073 92.662 92.646 92.460

Total Moisture Liquid collected, g 134 132.1 120 128.700

Volume of Water Vapor, standard cubic feet 6.31 6.22 5.65 6.060

Moisture Content of Stack Gas, % 6.41 6.29 5.75 6.150

Moisture Saturation at Stack Gas Temperature, % 84.90 87.01 86.21 86.040

Dry Mole Fraction 0.9359 0.9371 0.9425 0.939

Carbon Dioxide, % 7.876 7.912 7.912 7.900

Oxygen, % 11.223 11.259 11.259 11.247

Carbon Monoxide & Nitrogen, % 80.901 80.829 80.829 80.853

Fuel Factor 1.23 1.22 1.22

Dry Molecular Weight, lb/lb-Mole 29.71 29.72 29.72 29.717

Wet Molecular weight, lb/lb-Mole 28.96 28.98 29.05 28.997

Flue Gas Static Pressure, inches of H2O -0.5 -0.5 -0.48 -0.493

Absolute Flue Gas Pressure, inches of Mercury 29.76 29.76 29.76 29.760

Average Stack Gas Temperature, °F 203.63 204.83 204.38 204.280

Average Velocity Head, inches of H2O 0.9270032198

6469

0.959219428

925856

0.961865503

186964

0.949

Average Stack Gas Velocity, feet/second 60.67 61.75 61.74 61.387

Stack Cross-Sectional Area, square feet 452.389 452.389 452.389 452.389

Dry Volumetric Flow Rate, dry scfm 1,219,680.2 1,240,740.2 1,248,532.9 1,236,317.7

67

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,646,786.4 1,676,101.2 1,675,829.8 1,666,239.1

33

Percent Isokinetic of Sampling Rate, % 99.5 98.4 97.8 98.567

Percent Excess Air, % 110.7 111.7 111.7 111.367

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 288 288 288

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, January 13, 2011 Page 32 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 13, 2011 Page 33 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 10 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 13, 2011 Page 34 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 23

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, January 13, 2011 Page 35 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 13, 2011 Page 36 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 25A 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 13, 2011 Page 37 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, January 13, 2011 Page 38 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, January 13, 2011 Page 39 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 13, 2011 Page 40 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 6C 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 13, 2011 Page 41 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 13, 2011 Page 42 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - Method 7E 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, January 13, 2011 Page 43 of 44
Utility Boiler MACT ICR - Possum Point Power Station Unit 5

8/16/2010

Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, January 13, 2011 Page 44 of 44