Skip to Main Page ContentSkip to SearchSkip to Site Map NavigationSkip to Footer Links

        - Home

        - FAQ
        - Glossary
        - Facility Locator
        - What's New
        - Site Help
        - Index A-Z
        - Contact Us
        - Browse Aloud
        - Email Updates

Report a Safety Concern

      - Nuclear Reactors  - Power Reactors
- Research & Test Reactors
- Operating Reactors
- Operator Licensing
- New Reactors
- Advanced Reactors
- Operator Licensing for New Reactors
- Nuclear Reactor Quick Links
 
      - Nuclear Materials  - Special Nuclear Material
- Source Material
- Byproduct Material
- Med, Ind, & Academic Uses
- Source Materials Facilities
- Uranium Recovery
- Fuel Cycle Facilities
- Materials Transportation
- Nuclear Materials Quick Links
 
      - Radioactive Waste  - Low-Level Waste
- Waste Incidental to Reprocessing
- High-Level Waste
- Uranium Mill Tailings
- Low-Level Waste Disposal
- High-Level Waste Disposal
- Storage of Spent Nuclear Fuel
- Transporation of Spent Nuclear Fuel
- Radioactive Waste Quick Links
 
      - Nuclear Security  - Domestic Safeguards
- Information Security
- Radioactive Material Security
- Contact Us
 
      - Public Meetings & Involvement  - The NRC Approach to Open Government
- About Meetings Open to the Public
- Conferences & Symposia
- Documents for Comment
- Facilitating Stakeholder Involvement
- NRC Information Quality Guidelines
- Subscribe to E-mail Updates
- Commission Schedule
- Public Meeting Schedule
 
      - NRC Library  - Basic References
- Document Collections
- ADAMS Public Documents
- Public Document Room
- Get Copies of Documents
- FOIA & Privacy Act Requests
- Photos & Video
- Records Management 
- Withholding of Sensitive Information
- FAQ Index
- HLW Licensing Network
- Adjudications (Hearings)
 
      - About NRC  - The Commission
- Governing Legislation
- Plans, Budget, & Performance
- Organization & Functions
- Locations
- History
- Values
- Direction-Setting & Policymaking
- Radiation Protection
- Fire Protection
- How We Regulate
- Emergency Preparedness & Response
- Public Affairs
- Congressional Affairs
- International Programs
- State & Tribal Programs
- Alternative Dispute Resolution Programs
- Employment Opportunities
- Contracting Opportunities
- Grant Opportunities
- Civil Rights
 

PrintShare

Email

Print

TwitterFacebookMySpace

DelicousStumbleDigg

More...

HomeNRC LibraryDocument CollectionsGeneral CommunicationsInformation Notices1994

# 

```

UNITED STATES
NUCLEAR REGULATORY COMMISSION
OFFICE OF NUCLEAR REACTOR REGULATION
WASHINGTON, D.C.  20555

July 15, 1994


NRC INFORMATION NOTICE 94-51:  INAPPROPRIATE GREASING OF DOUBLE SHIELDED MOTOR
 BEARINGS


Addressees

All holders of operating licenses or construction permits for nuclear power
reactors.

Purpose

The U.S. Nuclear Regulatory Commission (NRC) is issuing this information
notice to alert addressees to the potential for failure of safety-related
equipment as a result of inappropriate greasing of double shielded motor
bearings.  It is expected that recipients will review the information for
applicability to their facilities and consider actions, as appropriate, to
avoid similar problems.  However, suggestions contained in this information
notice are not NRC requirements; therefore, no specific action or written
response is required.

Description of Circumstances

On January 20 and January 21, 1994, two different emergency diesel generator
fuel oil transfer pumps failed to start at the North Anna Power Station when
the motor breakers tripped on overload during testing.  On January 22, 1994,
the licensee tested the remaining six diesel fuel oil transfer pumps, and two
more of the pump motor breakers tripped on thermal overload.  These two pumps
supply the same diesel generator.  Consequently this diesel generator was
declared inoperable.

There are eight fuel oil transfer pumps at North Anna; two redundant pumps
supply each of the station four emergency diesel generators from underground
fuel oil storage tanks.  The transfer pumps are located in an unheated
building near the fuel oil tanks.  This building is continuously supplied with
outside air to reduce the oil fumes.  As a result, the temperature in the
building was about the same as that of the outdoor air, which was abnormally
cold: -15C [5F].  The licensee installed temporary heaters in the building
and, after a short warmup period, successfully tested all of the transfer
pumps.

Discussion

The licensee investigation of the problem showed that the failures to start
the pumps were caused by excessive grease in the motor bearings, which became
very stiff at the abnormally low temperatures.  This caused abnormally high
starting loads that prevented the motor from accelerating past the low

9407080037.                                        IN 94-51
                                        July 15, 1994
                                        Page 2 of 2


rotational speeds that cause the motor to draw high starting currents.  The
sustained high starting currents caused the motor power supply breaker thermal
overload devices to trip.

This determination was confirmed by placing the motors in a freezer for
2.5 hours at  -14C [6F] and applying power to them.  At this temperature
some of the motors drew 6 amperes when the rated 460 volts were applied to the
motor terminals, compared to the rated full load current of 0.75 amperes.
These motors continued to run at a slow speed in the start-up current range.
When tested at the same temperature after the bearings were replaced, the
motors ran at normal speed and drew only 0.4 amperes.

The motor bearings are of the double shielded type, which are supplied by
several different manufacturers, and normally require no greasing after they
are installed.  However, station records showed that 7 of the 8 motors had
been greased every 18 months since 1986.  The old bearings were found to be
completely full of grease.  According to the bearing vendors, a high grease
content inside the bearing shields could not only cause high starting loads,
but could also cause the bearing to overheat and solidify the grease under
normal operating conditions.

Related Generic Communications

NRC Information Notice 88-12, "Overgreasing of Motor Bearings," April 12,
1988.

NRC Information Notice 93-26 and Supplement 1, "Grease Solidification Causes
Molded-Case Circuit Breaker Failure To Close," April 7, 1993, and
January 31, 1994.

This information notice requires no specific action or written response.  If
you have any questions about the information in this notice, please contact
the technical contact listed below or the appropriate Office of Nuclear
Reactor Regulation project manager.

/s/'d by BKGrimes


                        Brian K. Grimes, Director
                        Division of Operating Reactor Support
                        Office of Nuclear Reactor Regulation

Technical contact:  Rick McWhorter, RII
                    (703) 894-5421

Attachment:
List of Recently Issued NRC Information Notices
```

*Page Last Reviewed/Updated Wednesday, February 16, 2011*

#### Home

            - News Releases
            - Event Reports
            - ADAMS
            - Open Gov
            - Students & Teachers
            - Photos & Video

#### About Us

            - Strategic Plan
            - Budget & Performance
            - Perf & Accountability Rept
            - History of the NRC
            - Employment
            - NRC Ethics
            - Agency Status

#### Popular Documents

            - Info Digest
            - Factsheets & Brochures
            - Forms
            - Electronic Submittals
            - NRC Reports – NUREG
            - NRC Regulations – 10-CFR
            - Inspection Reports
            - Plain Writing

#### Follow Along

            - Blog
            - RSS

Regulations.govUSA.govExpectMore.govRecoveryFOIANo Fear EEOInspector GeneralSite MapAccessibilityPrivacy PolicySite DisclaimerFor Employees