Facility _Information facility _id utility

_code legal_owner_nam e

legl_operator_name

legal_address_type

legal_address

legal_city legal_state legal_zip 10671 10671 AES Corporation AES Shady

Point, LLC legal ownerP.O. Box 1740 Panam a OK 74951

Page 1Facility _Information plant_nam e

physical_address

phyical_city

physical_state

physical_zip

ma iling_address

ma iling_city

ma iling_state

ma iling_zip AES Shady

Point,LLC 3 Miles East of Junction 31

Panam a OK 74951 P.O. Box 1740 Panam a OK 74951

Page 2Facility _Information RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas No TRUE FALSE FALSE FALSE FALSE TRUE FALSE FALSE

Page 3Facility _Information ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE FALSE Immediate notification of violations. Deviations are repoted on quarterly, semi-annual and annual reports No Oklahoma DEQ No analysis for Metals on coal received.No fuel composition analyis during 2008 stack test

Page 4Facility _Information No analysis for Metals on coal received.No fuel composition analysis during 2008 stack test

Page 5facility _contacts facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 10671 1 Environm ental Coordinator Bobbie Hull 9189626004 bobbie.hull@aes.com TRUE 10671 2 EHS Manager / VP Keith Brown

9189626020 keith.brown@aes.com FALSE 10671 3 VP Wi lliam M. Sanders 9189626019 mi ke.sanders@aes.com FALSE

Page 6facility _coal_utilized facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note 10671 bitum inous 30 30 10671 subbituminous 70 70

Page 7facility _oil_utilized facility _id oil_type percentage_volume percentage_btu

other_type

Page 8facility _other_materials facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain

Page 9facility _other_materials rcra_explain

Page 10boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuel heat_input max_heat_input MW e_capacity 10671 1A Fluidized bed firing Dry Bottom coal 3105 3552.7 283.92 10671 1b Fluidized bed firing Dry Bottom coal 3105 3552.7 283.92 10671 2a Fluidized bed firing Dry Bottom coal 3105 3552.7 283.92 10671 2b Fluidized bed firing Dry Bottom coal 3105 3552.7 283.92

Page 11boiler_information

MW e_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 245.51 0.81 0.88 1970 1970 1005 1000 FALSE 1005 245.51 81 88 1970 1970 1005 1000 FALSE 1005 245.51 81 88 1970 1970 1005 1000 FALSE 1005 245.51 81 88 1970 1970 1005 1000 FALSE 1005

Page 12boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 1000 7870.02 80.26 Subpart Da(1) FALSE FALSE 1000 8030.44 80.26 Subpart Da(1) FALSE FALSE 1000 7595.47 80.26 Subpart Da(1) FALSE FALSE 1000 7801.09 80.26 Subpart Da(1) FALSE

Page 13boiler_information

NOx_control

SO2_control

combustion_additives Yes Yes No Yes Yes No Yes Yes No Yes Yes No

Page 14boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 10671 1A coal - bituminous2007 30 30 10671 1A coal - bituminous2008 30 30 10671 1A coal - bituminous2009 30 30 10671 1A coal - subbituminous 2007 70 70 10671 1A coal - subbituminous 2008 70 70 10671 1A coal - subbituminous 2009 70 70 10671 1b coal - bituminous2007 30 30 10671 1b coal - bituminous2008 30 30 10671 1b coal - bituminous2009 30 30 10671 1b coal - subbituminous 2007 70 70 10671 1b coal - subbituminous 2008 70 70 10671 1b coal - subbituminous 2009 70 70 10671 2a coal - bituminous2007 30 30 10671 2a coal - bituminous2008 30 30 10671 2a coal - bituminous2009 30 30 10671 2a coal - subbituminous 2007 70 70 10671 2a coal - subbituminous 2008 70 70 10671 2a coal - subbituminous 2009 70 70 10671 2b coal - bituminous2007 30 30 10671 2b coal - bituminous2008 30 30 10671 2b coal - bituminous2009 30 30 10671 2b coal - subbituminous 2007 70 70 10671 2b coal - subbituminous 2008 70 70 10671 2b coal - subbituminous 2009 70 70

Page 15boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online 10671 1A Fluidized Bed Com bustor 1/1/1991 10671 1b Fluidized Bed Com bustor 1/1/1991 10671 2a Fluidized Bed Com bustor 1/1/1991 10671 2b Fluidized Bed Com bustor 1/1/1991

Page 16boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online 10671 1A Lim estone injection to fluidized bed-fired furnace 1/1/1991 10671 1b Lim estone injection to fluidized bed-fired furnace 1/1/1991 10671 2a Lim estone injection to fluidized bed-fired furnace 1/1/1991 10671 2b Lim estone injection to fluidized bed-fired furnace 1/1/1991

Page 17boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 18facility _units facility _id unit_id 10671 Unit 1 10671 Unit 2

Page 19unit_boilers

facility _id unit_id boiler_id 10671 Unit 1 1A 10671 Unit 1 1b 10671 Unit 2 2a 10671 Unit 2 2b

Page 20facility _controls facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 10671 U1 PM control Fabric Filter, pulse FALSE 1/1/1991 10671 U2 PM control Fabric Filter, pulse FALSE 1/1/1991

Page 21facility _controls reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive

Page 22facility _sampling_ports facility _id sampling_port_id 10671 Boiler 1A 10671 Boiler 1B 10671 Stack U1/2

Page 23facility _stacks facility _id stack_id stack_height stack_diameter

sack_gas_velocity 10671 AESSP U1/2 350 26 291420

Page 24configurations

facility _id configuration_id 10671 Unit 1 10671 Unit 2

Page 25configuration_components

facility _id configuration_id

component_id

order component_type port_near 10671 Unit 1 AESSP U1/2 3 Stack 10671 Unit 1 U1 2 PM control 10671 Unit 1 Unit 1 1 Unit 10671 Unit 2 AESSP U1/2 3 Stack 10671 Unit 2 U2 2 PM control 10671 Unit 2 Unit 2 1 Unit

Page 26configuration_pollutants1

facility _id configuration_id

pollutant_nam e

permit_type_1

em lim it_1 em lim it_units_1 avg_period_1

em lim it_2 em lim it_units_2 10671 Unit 2 Nitrogen Oxide (NOx) State - State Operating Permit

0.5 pound per million British Thermal Unit (lb/MMBtu)

30 days 1530 pound per hour (lb/hr) 10671 Unit 2 Sulfur Dioxide (SO2) State - State Operating Permit

1.2 pound per million British Thermal Unit (lb/MMBtu)

3 hours 0.6 pound per million British Thermal Unit (lb/MMBtu) 10671 Unit 2 PM (Filterable) State - State Operating Permit

0.03 pound per million British Thermal Unit (lb/MMBtu)

1 hour 10671 Unit 2 Carbon Monoxide (CO) State - State Operating Permit

610 pound per hour (lb/hr)

30 days 2672 tons per year (tons/yr) 10671 Unit 2 VOCs State - State Operating Permit 0.064 pound per million British Thermal Unit (lb/MMBtu)

1 hour 19.6 pound per hour (lb/hr) 10671 Unit 2 Beryllium (Be) State - State Operating Permit

0.0212 pound per hour (lb/hr)

1 hour 0.093 tons per year (tons/yr) 10671 Unit 2 Lead (Pb) State - State Operating Permit 1.96 pound per hour (lb/hr)

1 hour 8.58 tons per year (tons/yr) 10671 Unit 2 Total Mercury (Hgt) State - State Operating Permit

0.44 pound per hour (lb/hr)

1 hour 1.93 tons per year (tons/yr) 10671 Unit 1 PM (Filterable) State - State Operating Permit

0.03 pound per million British Thermal Unit (lb/MMBtu)

1 hour 90.4 pound per hour (lb/hr) 10671 Unit 1 Nitrogen Oxide (NOx) State - State Operating Permit

0.5 pound per million British Thermal Unit (lb/MMBtu)

30 days 1530 pound per hour (lb/hr) 10671 Unit 1 Sulfur Dioxide (SO2) State - State Operating Permit

1.2 pound per million British Thermal Unit (lb/MMBtu)

3 hours 0.6 pound per million British Thermal Unit (lb/MMBtu) 10671 Unit 1 Carbon Monoxide (CO) State - State Operating Permit

610 pound per hour (lb/hr)

1 hour 2672 tons per year (tons/yr) 10671 Unit 1 VOCs State - State Operating Permit 0.064 pound per million British Thermal Unit (lb/MMBtu)

1 hour 19.6 pound per hour (lb/hr) 10671 Unit 1 Beryllium (Be) State - State Operating Permit

0.0212 pound per hour (lb/hr)

1 hour 0.093 pound per million British Thermal Unit (lb/MMBtu) 10671 Unit 1 Lead (Pb) State - State Operating Permit 1.96 pound per hour (lb/hr)

1 hour 8.58 tons per year (tons/yr) 10671 Unit 1 Total Mercury (Hgt) State - State Operating Permit

0.44 pound per hour (lb/hr)

1 hour 1.93 tons per year (tons/yr)

Page 27configuration_pollutants1

avg_period_2

em lim it_3 em lim it_units_3 avg_period_3

em lim it_4 em lim it_units_4 avg_period_4

em lim it_details

test_method 30 days 6701 tons per year (tons/yr) Continuous 30 days 2363 pound per hour (lb/hr) 3 hours 10346 tons per year (tons/yr) Method 5 1 hour 30 days 85.8 tons per year (tons/yr) 1 hour 1 hour 1 hour 1 hour 1 hour 396 tons per year (tons/yr) 1 hour Method 5 30 days 6701 tons per year (tons/yr) Continuous 30 days 2363 pound per hour (lb/hr) 3 hours 10346 tons per year (tons/yr) Continuous 1 hour 1 hour 85.8 tons per year (tons/yr) 1 hour 1 hour 1 hour

Page 28configuration_pollutants1

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping

req_reporting 0.5 pound per million British Thermal Unit (lb/MMBtu)

No CEMS Contineous Quarterly Sem i-AnnualAnnual 0.75 pound per million British Thermal Unit (lb/MMBtu)

No CEMS Contineous Quarterly Sem i-AnnualAnnual 0.03 pound per million British Thermal Unit (lb/MMBtu)

No N/A N/a Annual 0.2 pound per million British Thermal Unit (lb/MMBtu)

No n/a n/a Annual 6 parts per million by

volum e (dry) (ppmvd) No n/a n/a Annual 0.0212 pound per million British Thermal Unit (lb/MMBtu)

No N/A n/a Annual 1.99 pound per million British Thermal Unit (lb/MMBtu)

No n/a n/a Annual 0.44 pound per million British Thermal Unit (lb/MMBtu)

No N/A n/A Annual 0.03 pound per million British Thermal Unit (lb/MMBtu)

No NA N/A Annual 0.5 pound per million British Thermal Unit (lb/MMBtu)

No CEMS N/A Quarterly Sem i-AnnualAnnual 0.75 pound per million British Thermal Unit (lb/MMBtu)

No CEMS N/A Quarterly Sem i-AnnualAnnual 0.2 pound per trillion British Thermal Unit (lb/1012Btu)

No N/A N/A Annual 6 parts per million by

volum e (dry) (ppmvd) No N/A N/A Annual 0.0212 pound per million British Thermal Unit (lb/MMBtu)

No N/A N/A Annual 1.99 pound per million British Thermal Unit (lb/MMBtu)

No N/A N/A Annual 0.44 pound per million British Thermal Unit (lb/MMBtu)

No N/A N/A Annual

Page 29configuration_pollutants1 Quarterly Sem i-AnnualAnnual Quarterly Sem i-AnnualAnnual

Quarterly Sem i-AnnualAnnual Quarterly Sem i-AnnualAnnual

Page 30control_technologies

facility _id configuration_id

component_id

control_id project_titleproject_type vendor_name

vndor_contact

vendor_phone

Page 31control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 32control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 33control_technologies feed_rate_units

Page 34control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 35control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_nam e

Page 36control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investm ent

total_operating_costs

base_year

Page 37control_costs

CBI

Page 38mi sc_controls

facility _id mi sc_control_id

control_description

Page 39mi sc_control_configurations

facility _id mi sc_control_id

configuration_id

Page 40fuel_shipments

facility _id shipment_id

shipment_date

am ount_received

am ount_units

fuel_type state_country other_country

county 10671 1 1/1/2009 101204 short tons (2000 lbs) coal Other Wyom ing 70% / OK 30% blend 10671 10 10/1/2009 129002.1 short tons (2000 lbs) coal 10671 11 11/1/2009 116537.2 short tons (2000 lbs) coal 10671 12 12/1/2009 142665.7 short tons (2000 lbs) coal 10671 3 9/1/2009 42332.57 short tons (2000 lbs) coal 10671 4 4/1/2009 92407.95 short tons (2000 lbs) coal 10671 5 5/1/2009 111960.8 short tons (2000 lbs) coal 10671 6 6/1/2009 118832 short tons (2000 lbs) coal 10671 7 7/1/2009 122003 short tons (2000 lbs) coal 10671 8 8/1/2009 119050 short tons (2000 lbs) coal 10671 9 9/1/2009 108319.7 short tons (2000 lbs) coal 10671 Sam ple 2 2/1/2009 92171.48 short tons (2000 lbs) coal

Page 41fuel_shipments

coal_seam shipment_method Wyom ing 70% / OK 30% blend Unit Train

Page 42fuel_shipment_configurations

facility _id shipment_id

configuration_id 10671 1 Unit 1 10671 1 Unit 2 10671 10 Unit 1 10671 10 Unit 2 10671 11 Unit 1 10671 11 Unit 2 10671 12 Unit 1 10671 12 Unit 2 10671 3 Unit 1 10671 3 Unit 2 10671 4 Unit 1 10671 4 Unit 2 10671 5 Unit 1 10671 5 Unit 2 10671 6 Unit 1 10671 6 Unit 2 10671 7 Unit 1 10671 7 Unit 2 10671 8 Unit 1 10671 8 Unit 2 10671 9 Unit 1 10671 9 Unit 2 10671 Sam ple 2 Unit 1 10671 Sam ple 2 Unit 2

Page 43fuel_shipment_samples

facility _id shipment_id

sample_id am ount_fuel am ount_fuel_units

total_sulfur ash_content heating_value

hating_units 10671 1 sample 1 5 gallons 1.49 11394 Btu/lb 10671 10 Sam ple 10 1.27 10985 Btu/lb 10671 11 Sam ple 11 1.38 10988 Btu/lb 10671 12 Sam ple 12 1.4 11019 Btu/lb 10671 3 Sam ple 3 5 gallons 1.64 10965 Btu/lb 10671 4 Sam ple 4 5 gallons 1.31 11159 Btu/lb 10671 5 Sam ple 5 5 gallons 1.28 11266 Btu/lb 10671 6 Sam ple 6 5 gallons 1.22 11266 Btu/lb 10671 7 Sam ple 7 1.53 11337 Btu/lb 10671 8 Sam ple 8 1.29 11189 Btu/lb 10671 9 Sam ple 9 1.13 11452 Btu/lb 10671 Sam ple 2 2 1.49 12619 Btu/lb

Page 44fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address permit requirements Other permit requirements Other permit requirements Other permit requirements Other permit requirements Other permit requirements Other permit requirements Other permit requirements Other permit requirements Other permit requirements Other permit requirements Other permit requirements Other

Page 45fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_nam e lab_address lab_city lab_state lab_zip analysis_copies No No No No No No No No No No No No

Page 46fuel_shipment_samples analysis_copies

Page 47fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL

Page 48test_reports

facility _id report_id report_type other_type report_description report_begin_date

report_end_date

before_control

during_deviation 10671 Stack Test 2008

other Stack test 2008 Title V renewal test

######## 12/5/2008 No No

Page 49test_reports

deviation_reports No

Page 50test_report_configurations

facility _id report_id configuration_id 10671 Stack Test 2008

Unit 1 10671 Stack Test 2008

Unit 2

Page 51test_report_fuels

facility _id report_id fuel_id 10671 Stack Test 2008

Ok / Wy Combined

Page 52test_report_fuel_types

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 10671 Stack Test 2008

Ok / Wy Combined

coal - bituminous 30 30 10671 Stack Test 2008

Ok / Wy Combined

coal - subbituminous

70 70

Page 53cem_data

facility _id tim e_period

cem_period_description 10671 Hourly for past 5 years

Page 54cem_data_pollutants1

facility _id tim e_period

pollutant_nam e 10671 Hourly Nitrogen Oxide (NOx) 10671 Hourly Sulfur Dioxide (SO2)

Page 55test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_bypass_percent

testing_bypass_percent 10671 Stack Test 2008

AESSP U1/2

No No

Page 56test_report_sampling

fg_fraction 100%

Page 57sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetim e

unit_load net_generation fg_moisture_content 10671 Stack Test 2008

AESSP U1/2

1 ######## ######## 368.38 321.58 11.38 10671 Stack Test 2008

AESSP U1/2

10 12/2/2008 12/2/2008 361.21 318.42 11.62 10671 Stack Test 2008

AESSP U1/2

2 ######## ######## 368.38 321.58 11.38 10671 Stack Test 2008

AESSP U1/2

3 ######## ######## 366.58 321.25 10.13 10671 Stack Test 2008

AESSP U1/2

4 ######## ######## 366.58 321.25 6.21 10671 Stack Test 2008

AESSP U1/2

5 12/2/2008 12/2/2008 361.21 318.42 11.62 10671 Stack Test 2008

AESSP U1/2

6 12/2/2008 12/2/2008 361.21 318.42 11.62 10671 Stack Test 2008

AESSP U1/2

7 ######## ######## 366.58 321.25 6.21 10671 Stack Test 2008

AESSP U1/2

8 ######## ######## 366.58 321.25 6.21 10671 Stack Test 2008

AESSP U1/2

9 12/2/2008 12/2/2008 361.21 318.42 11.62

Page 58sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 765743 dscfm 3.83 15.9 3.58 16.02 765743 dscfm 3.83 15.9 183193 dscfm 3.68 15.9 188624 dscfm 4.32 16.15 3.58 16.02 3.58 16.02 188624 dscfm 4.32 16.15 188624 dscfm 4.32 16.15 3.58 16.02

Page 59sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value 40 CFR Part 60, Appendix A, Reference Meth 1,2,3A, 4, 10, 19, 25A & 26

The AES Shady

Point facility

is a 40CFR Part 60 facility Ok / Wy Combined

368.38 6.21 8885 Ok / Wy Combined

361.21 11 8975.6 40 CFR Part 60, Appendix A, Reference Meth 1,2,3A, 4, 10, 19, 25A & 26

The AES Shady

Point facility

is a 40CFR Part 60 facility Ok / Wy Combined

368.38 6.21 8885 40 CFR Part 60, Appendix A, Reference Meth 1,2,3A, 4, 10, 19, 25A & 26

The AES Shady

Point facility

is a 40CFR Part 60 facility Ok / Wy Combined

366.58 9.99 9043.43 40 CFR Part 60, Appendix A, Reference Meth 1,2,3A, 4, 10, 19, 25A & 26

The AES Shady

Point facility

is a 40CFR Part 60 facility Ok / Wy Combined

366.58 9.99 9043.43 Ok / Wy Combined

361.21 11 8975.6 Ok / Wy Combined

361.21 11 8975.6 40 CFR Part 60, Appendix A, Reference Meth 1,2,3A, 4, 10, 19, 25A & 26

The AES Shady

Point facility

is a 40CFR Part 60 facility Ok / Wy Combined

366.58 9.99 9043.43 40 CFR Part 60, Appendix A, Reference Meth 1,2,3A, 4, 10, 19, 25A & 26

The AES Shady

Point facility

is a 40CFR Part 60 facility Ok / Wy Combined

366.58 9.99 9043.43 Ok / Wy Combined

361.21 11 8975.6

Page 60sampling_runs

fuel_sulfur 0.69 1.09 0.69 0.94 0.94 1.09 1.09 0.94 0.94 1.09

Page 61sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_nam e conc conc_units conc_ND conc_MDL 10671 Stack Test 2008

AESSP U1/2

1 VOCs 0.66 parts per million by volum e (dry) (ppmvd) FALSE 10671 Stack Test 2008

AESSP U1/2

1 Carbon Monoxide (CO) 8.06 parts per million by volum e (dry) (ppmvd) FALSE 10671 Stack Test 2008

AESSP U1/2

2 VOCs 1.29 parts per million by volum e (dry) (ppmvd) FALSE 10671 Stack Test 2008

AESSP U1/2

2 Carbon Monoxide (CO) 122.67 parts per million by volum e (dry) (ppmvd) FALSE 10671 Stack Test 2008

AESSP U1/2

3 PM (Filterable) FALSE 10671 Stack Test 2008

AESSP U1/2

4 PM (Filterable) FALSE 10671 Stack Test 2008

AESSP U1/2

5 PM (Filterable) FALSE 10671 Stack Test 2008

AESSP U1/2

6 PM (Filterable) FALSE 10671 Stack Test 2008

AESSP U1/2

7 PM (Filterable) FALSE 10671 Stack Test 2008

AESSP U1/2

8 PM (Filterable) FALSE 10671 Stack Test 2008

AESSP U1/2

9 PM (Filterable) FALSE 10671 Stack Test 2008

AESSP U1/2

10 PM (Filterable) FALSE

Page 62sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment 0.95 pound per hour (lb/hr)

FALSE 0 pound per million British Thermal Unit (lb/MMBtu) FALSE Wyom ing Coal 26.92 pound per hour (lb/hr)

FALSE 0.007 pound per million British Thermal Unit (lb/MMBtu) FALSE Wyom ing Coal 1.82 pound per hour (lb/hr)

FALSE 0 pound per million British Thermal Unit (lb/MMBtu) FALSE Oklahoma coal 400.46 pound per hour (lb/hr)

FALSE 0.109 pound per million British Thermal Unit (lb/MMBtu) FALSE Oklahoma Coal 123.3 pound per hour (lb/hr)

FALSE FALSE Wyom ing Boiler 1A 124.9 pound per hour (lb/hr)

FALSE FALSE Oklahoma 1A Boiler 123.3 pound per hour (lb/hr)

FALSE FALSE Wyom ing 1B Boiler 124.9 pound per hour (lb/hr)

FALSE FALSE Oklahoma 1B Boiler 123.3 pound per hour (lb/hr)

FALSE FALSE Wyom ing 2A Boiler 124.9 pound per hour (lb/hr)

FALSE FALSE Oklahoma 2A Boiler 123.3 pound per hour (lb/hr)

FALSE FALSE Wyom ing 2B Boiler 124.9 pound per hour (lb/hr)

FALSE FALSE Oklahoma 2B Boiler

Page 63sampling_run_pollutants1 run_pollutant_comment Wyom ing Coal Wyom ing Coal Oklahoma coal Oklahoma Coal Wyom ing Boiler 1A Oklahoma 1A Boiler Wyom ing 1B Boiler Oklahoma 1B Boiler Wyom ing 2A Boiler Oklahoma 2A Boiler Wyom ing 2B Boiler Oklahoma 2B Boiler

Page 64sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL

Page 65sampling_run_fuel fuel_conc_MDL

Page 66