Name: Andrew W. Oliver

Title: Environmental Manager

Company: Astoria Generating Company, L.P.

Sign Date: 9/10/2010

Name: Wesley W. Fritz

Title: Project Manager

Company: Weston Solutions, Inc.

Sign Date: 9/10/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Wednesday, January 19, 2011 Page 1 of 27
9/10/2010

Facility Information:

Astoria Generating Station - Stack 41

18-01 20th Avenue

Astoria NY 11105

Contact: Andrew Oliver

Phone: 315-433-1371

Fax:

Email: aoliver@uspowergen.com

Testing Company:

Weston Solutions, Inc.

1400 Weston Way

West Chester PA 19380

Contact:Wes Fritz

Phone: 610-701-3944

Fax:

Email: Wesley.Fritz@WestonSolutions.com

Air Permit Number:

8902

Permitted Source ID/Name:

40 Astoria Generating Station Unit 40 Stack 41

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Unit 40 discharges exhaust gases to two separate stacks. Testing was performed for each parameter of each grouping 

simultaneously on both stacks. Per EPA’s guidance, the test results are presented for each stack individually. The test 

results for each stack have not been combined or summed in this report. EPA will determine how the unit emissions 

will be summed following receipt of the test report and ERT submittal.

Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information:

AFS #: FRS #:

SCC / Description

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack 238.5 0 0 0 864 696 0 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Carbon Monoxide Method 10 3 0

Stack 2,3,7,8-TCDD Method 23 3 0

Stack 1,2,3,7,8-PeCDD Method 23 3 0

Stack 1,2,3,4,7,8-HxCDD Method 23 3 0

Stack 1,2,3,6,7,8-HxCDD Method 23 3 0

Stack 1,2,3,7,8,9-HxCDD Method 23 3 0

Stack 1,2,3,4,6,7,8-HpCDD Method 23 3 0

Wednesday, January 19, 2011 Page 2 of 27
9/10/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

See Attached Report

Stack OCDD Method 23 3 0

Stack 2,3,7,8-TCDF Method 23 3 0

Stack 1,2,3,7,8-PeCDF Method 23 3 0

Stack 2,3,4,7,8-PeCDF Method 23 3 0

Stack 1,2,3,4,7,8-HxCDF Method 23 3 0

Stack 1,2,3,6,7,8-HxCDF Method 23 3 0

Stack 2,3,4,6,7,8-HxCDF Method 23 3 0

Stack 1,2,3,7,8,9-HxCDF Method 23 3 0

Stack 1,2,3,4,6,7,8-HpCDF Method 23 3 0

Stack 1,2,3,4,7,8,9-HpCDF Method 23 3 0

Stack OCDF Method 23 3 0

Stack 3,3',4,4'-TCB (PCB77) Method 23 3 0

Stack 3,4,4',5-TCB (PCB81) Method 23 3 0

Stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 0

Stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 0

Stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 0

Stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 0

Stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Method 23 3 0

Stack 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 0

Stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Method 23 3 0

Total organic compounds 

(TOC) as Propane

Stack Method 25A 3 0

Stack Hydrogen Fluoride Method 26 3 0

Stack Hydrogen Chloride Method 26 3 0

Stack Filterable PM2.5 OTM - 27/28 3 0

Organic Condensible 

Particulate

Stack OTM - 27/28 3 0

Inorganic (Aqueous) 

Condensible Part.

Stack OTM - 27/28 3 0

Stack Selenium Method 29 3 0

Stack Manganese Method 29 3 0

Stack Phosphorus (yellow or white) Method 29 3 0

Stack Lead Method 29 3 0

Stack Nickel Method 29 3 0

Stack Antimony Method 29 3 0

Stack Arsenic Method 29 3 0

Stack Beryllium Method 29 3 0

Stack Cadmium Method 29 3 0

Stack Chromium Method 29 3 0

Stack Cobalt Method 29 3 0

Stack Filterable Particulate Method 29 0

Stack Co2 Method 3A CO2 3 0

Stack O2 Method 3A O2 3 0

Stack Sulfur Dioxide Method 6C 3 0

Stack Nitrogen oxides (NOx) Method 7E 3 0

Wednesday, January 19, 2011 Page 3 of 27
9/10/2010

Wednesday, January 19, 2011 Page 4 of 27
9/10/2010

Wednesday, January 19, 2011 Page 5 of 27
9/10/2010

Sampling / Stack Data Results Summary

Location Stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack - Method 23

Average

Run Number 1 2 3

Test Date 4/27/2010 4/28/2010 4/29/2010

Run Start Time 5:28:00 AM 7:08:00 

AM

6:33:00 AM

Run Finish Time 8:45:00 PM 7:57:00 PM 9:43:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 323.036 322.910 341.731 329.226

Moisture Content of Stack Gas, % 6.54 6.45 6.26 6.417

Moisture Saturation at Stack Gas Temperature, % 69.18 78.36 84.38 77.307

Carbon Dioxide, % 7 7.6 7.3 7.300

Oxygen, % 11.9 11.2 11.6 11.567

Average Stack Gas Temperature, °F 193.69 200.05 203.69 199.143

Dry Volumetric Flow Rate, dry scfm 191,453.4 191,453.2 204,195.3 195,700.633

Actual Wet Volumetric Flue Gas Flow Rate, acfm 255,579.8 255,579.8 273,263.8 261,474.467

Percent Isokinetic of Sampling Rate, % 102.3 102.3 101.5 102.033

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Wednesday, January 19, 2011 Page 6 of 27
9/10/2010

Location Stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack - Method 26

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Wednesday, January 19, 2011 Page 7 of 27
9/10/2010

Location Stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Wednesday, January 19, 2011 Page 8 of 27
9/10/2010

Location Stack - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Wednesday, January 19, 2011 Page 9 of 27
9/10/2010

Location Stack - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Wednesday, January 19, 2011 Page 10 of 27
9/10/2010

Emissions Summary

Location: Stack - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 0.00E+00 1.57E-04 7.84E-05 0.000

ppm 0.00E+00 1.07E-01 5.28E-02 0.053

ppm@7%O2 0.00E+00 1.57E-01 7.81E-02 0.078

Location: Stack - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000017 0.0000000019 0.000000046 0.000

lb/mmBtuO2 2.48E-13 2.57E-13 6.13E-12 0.000

ng/dscm 1.86E-04 2.08E-04 4.75E-03 0.002

ng/dscm@7%O2 2.87E-04 2.98E-04 7.10E-03 0.003

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000047 0.000000052 0.00000011 0.000

lb/mmBtuO2 6.85E-12 7.03E-12 1.47E-11 0.000

ng/dscm 5.14E-03 5.69E-03 1.14E-02 0.007

ng/dscm@7%O2 7.94E-03 8.15E-03 1.70E-02 0.011

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000033 0.0000000023 0.000000035 0.000

lb/mmBtuO2 4.81E-13 3.11E-13 4.66E-12 0.000

ng/dscm 3.61E-04 2.52E-04 3.62E-03 0.001

ng/dscm@7%O2 5.58E-04 3.61E-04 5.41E-03 0.002

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000023 0.0000000024 0.0000000021 0.000

lb/mmBtuO2 3.35E-13 3.24E-13 2.80E-13 0.000

ng/dscm 2.51E-04 2.63E-04 2.17E-04 0.000

ng/dscm@7%O2 3.88E-04 3.77E-04 3.24E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000019 0.00000003 0.0000000022 0.000

lb/mmBtuO2 2.77E-13 4.06E-12 2.93E-13 0.000

ng/dscm 2.08E-04 3.28E-03 2.27E-04 0.001

ng/dscm@7%O2 3.21E-04 4.70E-03 3.39E-04 0.002

Compound: 1,2,3,6,7,8-HxCDD

Average

Wednesday, January 19, 2011 Page 11 of 27
9/10/2010

RunNumber 1 2 3

Mass_mg 0.0000000023 0.0000000024 0.000000002 0.000

lb/mmBtuO2 3.35E-13 3.24E-13 2.66E-13 0.000

ng/dscm 2.51E-04 2.63E-04 2.07E-04 0.000

ng/dscm@7%O2 3.88E-04 3.77E-04 3.09E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000018 0.0000000028 0.000000033 0.000

lb/mmBtuO2 2.62E-13 3.79E-13 4.40E-12 0.000

ng/dscm 1.97E-04 3.06E-04 3.41E-03 0.001

ng/dscm@7%O2 3.04E-04 4.38E-04 5.10E-03 0.002

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000025 0.0000000023 0.0000000076 0.000

lb/mmBtuO2 3.64E-13 3.11E-13 1.01E-12 0.000

ng/dscm 2.73E-04 2.52E-04 7.86E-04 0.000

ng/dscm@7%O2 4.22E-04 3.61E-04 1.17E-03 0.001

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000023 0.0000000036 0.0000000026 0.000

lb/mmBtuO2 3.35E-13 4.87E-13 3.46E-13 0.000

ng/dscm 2.51E-04 3.94E-04 2.69E-04 0.000

ng/dscm@7%O2 3.88E-04 5.65E-04 4.02E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000059 0.0000000036 0.0000000027 0.000

lb/mmBtuO2 8.59E-13 4.87E-13 3.60E-13 0.000

ng/dscm 6.45E-04 3.94E-04 2.79E-04 0.000

ng/dscm@7%O2 9.96E-04 5.65E-04 4.17E-04 0.001

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000024 0.0000000099 0.0000000024 0.000

lb/mmBtuO2 3.50E-13 1.34E-12 3.20E-13 0.000

ng/dscm 2.62E-04 1.08E-03 2.48E-04 0.001

ng/dscm@7%O2 4.05E-04 1.55E-03 3.71E-04 0.001

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.0000000056 0.0000000053 0.000000015 0.000

lb/mmBtuO2 8.16E-13 7.17E-13 2.00E-12 0.000

ng/dscm 6.12E-04 5.80E-04 1.55E-03 0.001

ng/dscm@7%O2 9.45E-04 8.31E-04 2.32E-03 0.001

Wednesday, January 19, 2011 Page 12 of 27
9/10/2010

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.0000000038 0.0000000039 0.0000000061 0.000

lb/mmBtuO2 5.53E-13 5.27E-13 8.13E-13 0.000

ng/dscm 4.15E-04 4.27E-04 6.30E-04 0.000

ng/dscm@7%O2 6.41E-04 6.12E-04 9.42E-04 0.001

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.0000006 0.00000039 0.00000033 0.000

lb/mmBtuO2 8.74E-11 5.27E-11 4.40E-11 0.000

ng/dscm 6.56E-02 4.27E-02 3.41E-02 0.047

ng/dscm@7%O2 1.01E-01 6.12E-02 5.10E-02 0.071

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.0000000037 0.0000000038 0.000000006 0.000

lb/mmBtuO2 5.39E-13 5.14E-13 7.99E-13 0.000

ng/dscm 4.05E-04 4.16E-04 6.20E-04 0.000

ng/dscm@7%O2 6.26E-04 5.96E-04 9.27E-04 0.001

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.000000005 0.000000005 0.0000000019 0.000

lb/mmBtuO2 7.28E-13 6.76E-13 2.53E-13 0.000

ng/dscm 5.47E-04 5.47E-04 1.96E-04 0.000

ng/dscm@7%O2 8.45E-04 7.84E-04 2.93E-04 0.001

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.00000081 0.00000088 0.0000007 0.000

lb/mmBtuO2 1.18E-10 1.19E-10 9.33E-11 0.000

ng/dscm 8.86E-02 9.63E-02 7.23E-02 0.086

ng/dscm@7%O2 1.37E-01 1.38E-01 1.08E-01 0.128

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.000000013 0.000000006 0.000000007 0.000

lb/mmBtuO2 1.89E-12 8.11E-13 9.33E-13 0.000

ng/dscm 1.42E-03 6.56E-04 7.23E-04 0.001

ng/dscm@7%O2 2.19E-03 9.40E-04 1.08E-03 0.001

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000022 0.0000000033 0.000000039 0.000

lb/mmBtuO2 3.20E-13 4.46E-13 5.20E-12 0.000

Wednesday, January 19, 2011 Page 13 of 27
9/10/2010

ng/dscm 2.41E-04 3.61E-04 4.03E-03 0.002

ng/dscm@7%O2 3.72E-04 5.17E-04 6.02E-03 0.002

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000023 0.0000000032 0.000000032 0.000

lb/mmBtuO2 3.35E-13 4.33E-13 4.26E-12 0.000

ng/dscm 2.51E-04 3.50E-04 3.31E-03 0.001

ng/dscm@7%O2 3.88E-04 5.02E-04 4.95E-03 0.002

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000072 0.0000000087 0.0000000045 0.000

lb/mmBtuO2 1.05E-12 1.18E-12 6.00E-13 0.000

ng/dscm 7.87E-04 9.52E-04 4.65E-04 0.001

ng/dscm@7%O2 1.22E-03 1.36E-03 6.95E-04 0.001

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000005 0.000000012 0.0000000055 0.000

lb/mmBtuO2 7.28E-13 1.62E-12 7.33E-13 0.000

ng/dscm 5.47E-04 1.31E-03 5.68E-04 0.001

ng/dscm@7%O2 8.45E-04 1.88E-03 8.49E-04 0.001

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.0000000039 0.000000004 0.0000000062 0.000

lb/mmBtuO2 5.68E-13 5.41E-13 8.26E-13 0.000

ng/dscm 4.26E-04 4.38E-04 6.41E-04 0.001

ng/dscm@7%O2 6.58E-04 6.28E-04 9.58E-04 0.001

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000051 0.0000000051 0.000000016 0.000

lb/mmBtuO2 7.43E-13 6.89E-13 2.13E-12 0.000

ng/dscm 5.58E-04 5.58E-04 1.65E-03 0.001

ng/dscm@7%O2 8.62E-04 8.00E-04 2.47E-03 0.001

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.0000000073 0.0000000027 0.00000001 0.000

lb/mmBtuO2 1.06E-12 3.65E-13 1.33E-12 0.000

ng/dscm 7.98E-04 2.95E-04 1.03E-03 0.001

ng/dscm@7%O2 1.23E-03 4.23E-04 1.54E-03 0.001

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Wednesday, January 19, 2011 Page 14 of 27
9/10/2010

Mass_mg 0.0000000071 0.0000000026 0.0000000083 0.000

lb/mmBtuO2 1.03E-12 3.51E-13 1.11E-12 0.000

ng/dscm 7.76E-04 2.84E-04 8.58E-04 0.001

ng/dscm@7%O2 1.20E-03 4.07E-04 1.28E-03 0.001

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000038 0.0000000034 0.0000000033 0.000

lb/mmBtuO2 5.53E-13 4.60E-13 4.40E-13 0.000

ng/dscm 4.15E-04 3.72E-04 3.41E-04 0.000

ng/dscm@7%O2 6.41E-04 5.33E-04 5.10E-04 0.001

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000058 0.0000000058 0.0000000037 0.000

lb/mmBtuO2 8.45E-13 7.84E-13 4.93E-13 0.000

ng/dscm 6.34E-04 6.34E-04 3.82E-04 0.001

ng/dscm@7%O2 9.79E-04 9.09E-04 5.71E-04 0.001

Location: Stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 0.00E+00 2.10E-03 9.42E-04 0.001

ppm 0.00E+00 9.06E-01 4.03E-01 0.436

ppm@7%O2 0.00E+00 1.33E+00 5.96E-01 0.642

Location: Stack - Method 26

Compound: Hydrogen Chloride

Average

RunNumber 3 1 2

Mass_mg 0.78 0.82 0.81 0.803

lb/mmBtuO2 3.95E-04 4.34E-04 4.35E-04 0.000

ppm 2.02E-01 2.13E-01 2.11E-01 0.209

ppm@7%O2 3.02E-01 3.33E-01 3.33E-01 0.323

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.25 0.25 0.25 0.250

lb/mmBtuO2 1.32E-04 1.34E-04 1.27E-04 0.000

ppm 1.18E-01 1.18E-01 1.18E-01 0.118

ppm@7%O2 1.84E-01 1.86E-01 1.76E-01 0.182

Location: Stack - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.668 0.61 0.588 0.622

lb/mmBtuO2 1.89E-04 1.76E-04 1.73E-04 0.000

Wednesday, January 19, 2011 Page 15 of 27
9/10/2010

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.00946 0.00776 0.00726 0.008

lb/mmBtuO2 2.67E-06 2.24E-06 2.13E-06 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00264 0.00232 0.00223 0.002

lb/mmBtuO2 7.46E-07 6.71E-07 6.56E-07 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00075 0.00075 0.00075 0.001

lb/mmBtuO2 2.12E-07 2.17E-07 2.20E-07 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.01875 0.00465 0.00667 0.010

lb/mmBtuO2 5.30E-06 1.34E-06 1.96E-06 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.11625 0.09815 0.09113 0.102

lb/mmBtuO2 3.29E-05 2.84E-05 2.68E-05 0.000

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 64.9 39.9 35.2 46.667

lb/mmBtuO2 1.83E-02 1.15E-02 1.03E-02 0.013

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.02643 0.02323 0.02747 0.026

lb/mmBtuO2 7.47E-06 6.72E-06 8.08E-06 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.30151 0.23681 0.23621 0.258

lb/mmBtuO2 8.52E-05 6.85E-05 6.94E-05 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 2.09837 1.80821 1.71987 1.875

lb/mmBtuO2 5.93E-04 5.23E-04 5.06E-04 0.001

Wednesday, January 19, 2011 Page 16 of 27
9/10/2010

Process Run Data

Compound: Phosphorus (yellow or white)

Average

RunNumber 1 2 3

Mass_mg 0.364 0.295 0.279 0.313

lb/mmBtuO2 1.03E-04 8.53E-05 8.20E-05 0.000

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0075 0.0075 0.0075 0.008

lb/mmBtuO2 2.12E-06 2.17E-06 2.20E-06 0.000

Location: Stack - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 2.88E-01 2.82E-01 2.83E-01 0.284

ppm 8.02E+01 7.76E+01 8.24E+01 80.067

ppm@7%O2 1.25E+02 1.23E+02 1.23E+02 123.667

Location: Stack - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 1.72E-01 1.79E-01 1.70E-01 0.174

ppm 6.67E+01 6.88E+01 6.88E+01 68.100

ppm@7%O2 1.04E+02 1.09E+02 1.03E+02 105.333

Location: Stack - OTM - 27/28

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 19.3 15.2 14.6 16.367

lb/mmBtuO2 6.78E-03 5.64E-03 5.47E-03 0.006

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 6.2 7.3 6.5 6.667

lb/mmBtuO2 2.18E-03 2.71E-03 2.44E-03 0.002

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 1 1 1 1.000

lb/mmBtuO2 3.51E-04 3.71E-04 3.75E-04 0.000

Wednesday, January 19, 2011 Page 17 of 27
9/10/2010

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Gross Electric Output 85.5 MW 0

2 Gross Electric Output 91 MW 0

3 Gross Electric Output 85 MW 0

4 Gross Electric Output 89.5 MW 0

5 Gross Electric Output 85.1 MW 0

Run Name Value UOM Comments

1 0

Wednesday, January 19, 2011 Page 18 of 27
9/10/2010

Sampling / Stack Data Results Detail

Location Stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Wednesday, January 19, 2011 Page 19 of 27
9/10/2010

Location Stack - Method 23

Average

Run Number 1 2 3

Test Date 4/27/2010 4/28/2010 4/29/2010

Run Start Time 5:28:00 AM 7:08:00 AM 6:33:00 AM

Run Finish Time 8:45:00 PM 7:57:00 PM 9:43:00 PM

Net Traversing Points 96 95 96

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.442 0.442 0.442 0.442

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.0022 1.0022 1.0022 1.002

Barometric Pressure, inches of Mercury 29.71 29.97 30 29.893

Average Orifice Meter Differential, inches H2O 1.53 1.52 1.75 1.600

Dry Gas Meter Volume Sampled, cubic feet 315.027 316.548 341.883 324.486

Average Dry Gas Meter Temperature, °F 54.36 61.54 73.09 62.997

Dry Gas Meter Volume Sampled, dscf 323.036 322.910 341.731 329.226

Total Moisture Liquid collected, g 480.5 472.7 485.1 479.433

Volume of Water Vapor, standard cubic feet 22.62 22.25 22.83 22.567

Moisture Content of Stack Gas, % 6.54 6.45 6.26 6.417

Moisture Saturation at Stack Gas Temperature, % 69.18 78.36 84.38 77.307

Dry Mole Fraction 0.9346 0.9355 0.9374 0.936

Carbon Dioxide, % 7 7.6 7.3 7.300

Oxygen, % 11.9 11.2 11.6 11.567

Carbon Monoxide & Nitrogen, % 81.1 81.2 81.1 81.133

Fuel Factor 1.29 1.28 1.27

Dry Molecular Weight, lb/lb-Mole 29.60 29.66 29.63 29.630

Wet Molecular weight, lb/lb-Mole 28.84 28.91 28.90 28.883

Flue Gas Static Pressure, inches of H2O -0.27 -0.27 -0.27 -0.270

Absolute Flue Gas Pressure, inches of Mercury 29.69 29.95 29.98 29.873

Average Stack Gas Temperature, °F 193.69 200.05 203.69 199.143

Average Velocity Head, inches of H2O 4.7864644314

7564E-02

4.797516952

76979E-02

0.054553510

589674

0.050

Average Stack Gas Velocity, feet/second 13.73 13.73 14.68 14.047

Stack Cross-Sectional Area, square feet 310.245 310.245 310.245 310.245

Dry Volumetric Flow Rate, dry scfm 191,453.4 191,453.2 204,195.3 195,700.633

Actual Wet Volumetric Flue Gas Flow Rate, acfm 255,579.8 255,579.8 273,263.8 261,474.467

Percent Isokinetic of Sampling Rate, % 102.3 102.3 101.5 102.033

Percent Excess Air, % 125.1 109.4 118.2 117.567

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 238.5 238.5 238.5

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Wednesday, January 19, 2011 Page 20 of 27
9/10/2010

Location Stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Wednesday, January 19, 2011 Page 21 of 27
9/10/2010

Location Stack - Method 26

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Wednesday, January 19, 2011 Page 22 of 27
9/10/2010

Location Stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Wednesday, January 19, 2011 Page 23 of 27
9/10/2010

Location Stack - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Wednesday, January 19, 2011 Page 24 of 27
9/10/2010

Location Stack - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Wednesday, January 19, 2011 Page 25 of 27
9/10/2010

Location Stack - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Wednesday, January 19, 2011 Page 26 of 27
9/10/2010

Location Stack - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Wednesday, January 19, 2011 Page 27 of 27
9/10/2010

Location Stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Wednesday, January 19, 2011 Page 28 of 27