### Instructions for filling in the Emission Test Template

This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate runs or sampling events for each of the requested constituents. This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. yellow are required. All cells that are shaded in green are populated using drop

- down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls (example: 8100_Unit_2_EmisTestMethods.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet. 2. Please enter the control device configuration.

Emission Data Worksheets

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg Hg +2

### , or if the Ontario

- Hydro Method was used, you would need to enter Hg0

### , HgP, and Hg Volatile Organic HAP and Speciated Semi

-Volatile Organic HAP worksheets allow you to use a drop Constituent field to define as many records as needed to record each HAP that you have results for. General instructions follow for these worksheets:

Boiler Operation Information

1. Please provide the values of all requested parameters for each of test run/sample. 2. Please provide any other supporting information or comments in the Other Supporting Information field.

Fuel Information

1. Please enter what types of fuel are being used in your boiler using the drop

- downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples, then enter an input rate of zero. 2. Please enter the unit of measure using the drop down provided. 3. Please enter the test method used to determine the fuel input rate. 4. Please provide any other information that you feel may be important in the Other Supporting Information field.

Emission Data

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and ppmvd @ 7% O 2 

### (parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please also enter these data.

### This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. Fields shaded in down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet.

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg0 

### and , HgP, and Hg+2 

### . However, both the Speciated Volatile Organic HAP worksheets allow you to use a drop

- down provided in the Constituent field to define as many records as needed to record each HAP that you have results for. General instructions

2. Please provide any other supporting information or comments in the Other Supporting Information field.

downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples,

4. Please provide any other information that you feel may be important in the Other Supporting Information field.

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and

(parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please alsoEIA

Facility Code Facility Name Boiler ID

2451 San Juan Unit 2Control Device Configuraton

Listed (by

boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICRListed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICREIA

Facility Code Facility Name Boiler ID 2451 San Juan Unit 2

1 4/26/2010 13:10 1 4/26/2010 13:10 2 4/27/2010 7:10 2 4/27/2010 7:10 3 4/27/2010 11:10 3 4/27/2010 11:10 Run Number Test Start Date Test Start TimePlease note QA/QC documentation starting in Column "AI"

Measured Value (μg/dscm) Basis (Wet or Dry)

4/26/2010 16:10 0.072 Dry 4/26/2010 16:10 0.084 Dry 4/27/2010 10:10 0.061 Dry 4/27/2010 10:10 0.083 Dry 4/27/2010 15:53 0.071 Dry 4/27/2010 15:53 0.067 Dry Total Vapor Phase Mercury Emission Test Results

Test End Time Test End DatePlease note QA/QC documentation starting in Column "AI"

Test Method Used Data Flag (ADL, BDL, DDL) Test Method

Comments (lb/mmBtu)

U.S. EPA Method 30B 0.000000067 2157 U.S. EPA Method 30B 0.000000067 2157 U.S. EPA Method 30B 0.000000056 2190 U.S. EPA Method 30B 0.000000056 2190 U.S. EPA Method 30B 0.000000060 2190 U.S. EPA Method 30B 0.000000060 2190 Total Vapor Phase Mercury Emission Test Results Steam Output (1000 lb/hr)Fuel Input Rate

3379 10.3 12.94 6.21 876652 116.8 352033 3379 10.3 12.94 6.21 876652 116.8 352033 3359 10.3 12.75 6.42 884700 116.6 368579 3359 10.3 12.75 6.42 884700 116.6 368579 3178 11.2 12.68 6.5 846533 119.1 344918 3178 11.2 12.68 6.5 846533 119.1 344918 Flue Gas O 2(%) Flue Gas

Flow Rate (dscfm) Flue Gas Moisture (%) Total Heat Input (mmBtu/hr) Flue Gas CO 2(%) Flue Gas Temperature (F)QA /QC Documentation

Fuel Type Units of

Measure Measurement

Method Trap ID Section 1 Mass (ng)
subbituminous lb/hour F-Factor 60058 38.2 subbituminous lb/hour F-Factor 60028 37.8 subbituminous lb/hour F-Factor 60032 38.8 subbituminous lb/hour F-Factor 60048 38.2 subbituminous lb/hour F-Factor 58839 39.5 subbituminous lb/hour F-Factor 60031 38.2

Fuel #1 Other Supporting InformationQA /QC Documentation

Section 2 Mass (ng) Total

Mass (ng) Initial

Spike (ng) Total NonSpike (ng) Sample

Volume (dscm) Volume

Difference (%) Volume Diff. Limit Breaktrough

(%)
3.7 41.9 30 11.9 0.146881 9.685863874 6.6 44.4 30 14.4 0.14576 17.46031746 1.1 39.9 30 9.9 0.150228 2.835051546 2 40.2 30 10.2 0.14899 5.235602094 2 41.5 30 11.5 147.249 5.063291139 1.4 39.6 30 9.6 0.048693 3.664921466 ≤20% of field recovery test Trap #1Breaktrough

Limit Concentration

(μg/dscm) Trap ID Section 1 Mass Section 2

Mass Total

Mass Initial

Spike Total NonSpike
0.081017967 60920 8.7 0.5 9.2 0 9.2 0.098792536 60882 9.4 0.5 9.9 0 9.9 0.065899832 60886 7.6 0.8 8.4 0 8.4 0.068460971 60852 13.1 1.4 14.5 0 14.5 7.8099E-05 60871 8.6 0.7 9.3 0 9.3 0.197152245 60897 8.6 1.3 9.9 0 9.9 ≤10% of Section 1 Hg

mass for Hg conc. >1
μg/dscm: or ≤ 20% of SectionSample

Volume Volume

Difference (%) Volume Diff. Limit Breaktrough (%) Breaktrough Limit Concentration

(μg/dscm)
0.146625 5.747126437 0.062745098 0.14486 5.319148936 0.068341847 0.149909 10.52631579 0.056033994 0.148104 10.6870229 0.097904175 0.147019 8.139534884 0.06325713 0.145369 15.11627907 0.068102553 ≤10% of Section 1 Hg mass for Hg conc. >1
μg/dscm: or ≤ 20% of Section 1 for Hg conc. ≤1 ≤20% of field recovery test Trap #2Abs. diff. RD (%) Limit C rec R (%) by Run Ravg(%) Limit

0.018273 12.71041 29.4438 98.1 0.030451 18.21928 28.3795 94.6 0.009866 8.091141 31.2474 104.2 0.029443 17.69794 24.9227 83.1 0.063179 99.75338 30.8772 102.9 0.12905 48.65122 29.5129 98.4

≥ 10 % RD mass for Hg conc. >1 μg/dscm: or
≤20% RD or ≤ 0.2 μg/dscm abs.diff. for Hg conc. ≤1 Average Recovery

, between 85 and 115% Measured Spike Recovery ( R )

96.88333333 Paired Trap Agreement (RD)EIA

Facility Code Facility Name Boiler ID

2451 San Juan Unit 2

1 4/27/2010 9:02 4/27/2010 2 4/28/2010 7:06 4/28/2010 3 4/29/2010 7:25 4/29/2010 Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry)
13:35 0.02 Dry 12:05 0.02 Dry 12:07 0.02 Dry Test End TimeTest Method Used Data Flag (ADL, BDL, DDL) Test Method

Comments U.S. EPA Conditional Test Method 033 (CTM-033) 0.0000240 U.S. EPA Conditional Test Method 033 (CTM-033) 0.0000197 U.S. EPA Conditional Test Method 033 (CTM-033) 0.0000228 Analysis was non detect for HCN and detectition lim it was substituted Calculated

Emission Rate (lb/mmBtu) Hydrogen Cyanide Emission Test ResultsFuel Input Rate 2190 3331 12.2 12.8 6.2 786231 114 361391 2191 3553 13 12.8 6.3 838146 115 389773 2253 3503 14 12.7 6.4 850541 114 385969 Flue Gas Temperature (F) Flue Gas Moisture (%) Flue Gas CO 2(%) Flue Gas

O 2(%) Flue Gas

Flow Rate (dscfm) Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr)Fuel Type Units of Measure Measurement

Method subbituminous

lb/hour F-Factor subbituminous

lb/hour F-Factor subbituminous

lb/hour F-Factor Other Supporting Information Fuel #1EIA

Facility Code Facility Name Boiler ID 2451 San Juan Unit 2

1 4/26/2010 13:10 2 4/27/2010 7:10 3 4/27/2010 11:10 Run Number Test Start Date Test Start TimeTotal Dissolved Solids (mg solids/liter) Total Suspended Solids (mg solids/liter)
4/26/2010 16:10 51700 113674 4/27/2010 10:10 56900 122840 4/27/2010 15:53 43420 115050

Test End Time Test End DateTest Method Used Data Flag (ADL, BDL, DDL) Constisuent Emission Test ResultsTest Method Comments Fuel Input Rate

2463 3379 876652 116.8 352033 3081 3359 884700 116.6 368579 3081 3178 846533 119.1 344918 Flue Gas Temperat ure (F) Flue Gas Flow Rate (dscfm) Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr)Fuel Type Units of Measure Measurement

Method
subbituminous lb/hour F-Factor subbituminous lb/hour F-Factor subbituminous lb/hour F-Factor Other Supporting Information

Fuel #1