Skip to Main Page ContentSkip to SearchSkip to Site Map NavigationSkip to Footer Links

        - Home

        - FAQ
        - Glossary
        - Facility Locator
        - What's New
        - Site Help
        - Index A-Z
        - Contact Us
        - Email Updates
        -    Listen to page

Report a Safety Concern

      - Nuclear Reactors  - Power Reactors
- Research & Test Reactors
- Operating Reactors
- Operator Licensing
- New Reactors
- Operator Licensing for New Reactors
- Research Activities
- Nuclear Reactor Quick Links
 
      - Nuclear Materials  - Special Nuclear Material
- Source Material
- Byproduct Material
- Med, Ind, & Academic Uses
- Radium
- Uranium Recovery
- Fuel Cycle Facilities
- Materials Transportation
- Research Activities
- Nuclear Materials Quick Links
 
      - Radioactive Waste  - Decommissioning of Nuclear Facilities
- Low-Level Waste
- Waste Incidental to Reprocessing
- High-Level Waste
- Uranium Mill Tailings
- Low-Level Waste Disposal
- High-Level Waste Disposal
- Storage of Spent Nuclear Fuel
- Transportation of Spent Nuclear Fuel
- Research Activities
- Radioactive Waste Quick Links
 
      - Nuclear Security  - Domestic Safeguards
- Information Security
- Radioactive Material Security
- Required Reporting for Clearance Holders
- Insider Threat Program for Licensees
- Criminal History & Firearms Checks
- Contact Us
 
      - Public Meetings & Involvement  - The NRC Approach to Open Government
- About Meetings Open to the Public
- Conferences & Symposia
- Documents for Comment
- NRC Rules and Petitions
- Facilitating Stakeholder Involvement
- NRC Information Quality Guidelines
- Subscribe to E-mail Updates
- Commission Schedule
- Adjudications (Hearings)
- Public Meeting Schedule
- Adjudicatory Submissions
 
      - NRC Library  - Basic References
- Document Collections
- ADAMS Public Documents
- Public Document Room
- LSN Library
- FOIA & Privacy Act
- Records Management
- Training Courses
- FAQ Index
- Get Copies of Documents
- Withholding of Sensitive Information
- Photos & Video
- Electronic Hearing Docket
 
      - About NRC  - The Commission
- Organization & Functions
- Governing Legislation
- Plans, Budget, & Performance
- Locations
- History
- Values
- Direction-Setting & Policymaking
- Research Activities
- Radiation Protection
- Fire Protection
- Safety Culture
- How We Regulate
- Emergency Preparedness & Response
- Public Affairs
- Congressional Affairs
- Enforcement
- International Programs
- State & Tribal Programs
- Alternative Dispute Resolution Programs
- Privacy Program
- Civil Rights
- Contact Us
- Career Opportunities
- Contracting Opportunities
- Small Businesses
- Grant Opportunities
 

Print

HomeNRC LibraryDocument CollectionsGeneric CommunicationsInformation Notices1980

# Information Notice No.80-03 - Main Turbine Electrohydraulic Control System

```
                                                            SSINS No.: 6870 
                                                            Accession No.:
                                                            7912190666 

                                UNITED STATES
                        NUCLEAR REGULATORY COMMISSION
                    OFFICE OF INSPECTION AND ENFORCEMENT
                           WASHINGTON, D.C. 20555 

                             January 31, 1980  

                                           Information Notice No. 80-03 

MAIN TURBINE ELECTROHYDRAULIC CONTROL SYSTEM 

Description of Circumstances: 

On September 6, 1979, while performing a routine startup of the Trojan 
Nuclear Plant, a speed control problem was encountered during warmup of the 
General Electric turbine and increase of turbine speed to normal operating 
speed (1800 RPM). Technicians were notified and trouble shooting in 
accordance with the technical manual* was commenced to resolve the apparent 
oscillation between the primary and backup speed control circuits which was 
hindering normal turbine startup operations. The technical manual indicates 
that it is permissible to remove either the primary or backup low value gate
circuits which contain speed and acceleration error amplifiers. Upon removal
of the primary low value gate circuits which contain speed and acceleration 
error amplifiers. Upon removal of the primary low value gate circuit card, 
the backup card amplifiers, coming from a saturated condition, became the 
controlling circuit. During the shift in control circuits (primary to 
backup), the speed/acceleration error signal went to maximum which resulted 
in a full open signal to the turbine control valves. Under existing plant 
conditions this appeared to the safety injection system as a major steam 
break downstream of the main steam isolation valves which resulted in a 
safety injection system actuation and reactor trip. 

The Electrohydraulic Control System (EHC) technical manual indicated that 
slight load changes are likely when a low value gate card is removed. The 
effect on an unloaded turbine appears to be much more significant and tests 
conducted by 

*GEK Instruction Book 11381-D, "Speed Control Unit", Maintenance Section, 
Page 4. 
.

Information Notice No. 80-03                             January 31, 1980 
                                                            Page 2 of 2 

Trojan personnel indicate that the transient is initiated whether the 
turbine is at a set speed or in an acceleration mode to a set speed. 
Discussions with General Electric personnel by the licensee have been 
initiated in an attempt to verify the phenomenon observed and, if 
applicable, alert other facilities which operate a turbine with a MK 1 EHC 
System regarding the potential operation of the control valves when trouble 
shooting the speed control unit in accordance with existing instructions. 

This information is provided as an early notification of a possible 
significant matter. It is expected that recipients will review the 
information for possible applicability to their facilities. No specific 
action or response is requested to at this time. If further NRC evaluations 
so indicate, an IE Circular or Bulletin will be issued to recommend or 
request specific licensee actions. If you have questions regarding this 
matter, please contact the. Director of the appropriate NRC Regional Office.

Enclosure: 
List of Recently Issued 
     IE Information Notices
```

*Page Last Reviewed/Updated Friday, May 22, 2015*

#### Home

            - News Releases
            - Event Reports
            - ADAMS
            - Open Gov
            - Digital Government
            - The Student Corner
            - Photos & Video
            - For Developers

#### About Us

            - Strategic Plan
            - Budget & Performance
            - Agency Financial Report
            - License Fees
            - History of the NRC
            - Career Opportunities
            - NRC Ethics
            - Agency Status
            - Contact Us

#### Popular Documents

            - Info Digest
            - Fact Sheets & Brochures
            - Forms
            - Electronic Submittals Application
            - Adjudicatory Submissions
            - NRC Reports – NUREG
            - NRC Regulations – 10-CFR
            - Inspection Reports
            - Plain Writing
            - Enforcement Actions
            - RULEMAKING

#### Stay Connected

            - Blog
            - Facebook
            - Twitter
            - YouTube
            - Flickr
            - GovDelivery
            - RSS

Regulations.govUSA.govRecoveryFOIANo Fear EEOInspector General ProgramSite MapAccessibilityPrivacy PolicySite DisclaimerFor Employees