Skip to Main Page ContentSkip to SearchSkip to Site Map NavigationSkip to Footer Links

        - Home

        - FAQ
        - Glossary
        - Facility Locator
        - What's New
        - Site Help
        - Index A-Z
        - Contact Us
        - Email Updates
        -    Listen to page

Report a Safety Concern

      - Nuclear Reactors  - Power Reactors
- Research & Test Reactors
- Operating Reactors
- Operator Licensing
- New Reactors
- Operator Licensing for New Reactors
- Research Activities
- Nuclear Reactor Quick Links
 
      - Nuclear Materials  - Special Nuclear Material
- Source Material
- Byproduct Material
- Med, Ind, & Academic Uses
- Radium
- Uranium Recovery
- Fuel Cycle Facilities
- Materials Transportation
- Research Activities
- Nuclear Materials Quick Links
 
      - Radioactive Waste  - Decommissioning of Nuclear Facilities
- Low-Level Waste
- Waste Incidental to Reprocessing
- High-Level Waste
- Uranium Mill Tailings
- Low-Level Waste Disposal
- High-Level Waste Disposal
- Storage of Spent Nuclear Fuel
- Transportation of Spent Nuclear Fuel
- Research Activities
- Radioactive Waste Quick Links
 
      - Nuclear Security  - Domestic Safeguards
- Information Security
- Radioactive Material Security
- Required Reporting for Clearance Holders
- Insider Threat Program for Licensees
- Criminal History & Firearms Checks
- Contact Us
 
      - Public Meetings & Involvement  - The NRC Approach to Open Government
- About Meetings Open to the Public
- Conferences & Symposia
- Documents for Comment
- NRC Rules and Petitions
- Facilitating Stakeholder Involvement
- NRC Information Quality Guidelines
- Subscribe to E-mail Updates
- Commission Schedule
- Adjudications (Hearings)
- Public Meeting Schedule
- Adjudicatory Submissions
 
      - NRC Library  - Basic References
- Document Collections
- ADAMS Public Documents
- Public Document Room
- LSN Library
- FOIA & Privacy Act
- Records Management
- Training Courses
- FAQ Index
- Get Copies of Documents
- Withholding of Sensitive Information
- Photos & Video
- Electronic Hearing Docket
 
      - About NRC  - The Commission
- Organization & Functions
- Governing Legislation
- Plans, Budget, & Performance
- Locations
- History
- Values
- Direction-Setting & Policymaking
- Research Activities
- Radiation Protection
- Fire Protection
- Safety Culture
- How We Regulate
- Emergency Preparedness & Response
- Public Affairs
- Congressional Affairs
- Enforcement
- International Programs
- State & Tribal Programs
- Alternative Dispute Resolution Programs
- Privacy Program
- Civil Rights
- Contact Us
- Career Opportunities
- Contracting Opportunities
- Small Businesses
- Grant Opportunities
 

Print

HomeNRC LibraryDocument CollectionsGeneric CommunicationsInformation Notices1980

# Information Notice No.80-31 - Maloperation of Gould-Brown Boveri 480 Volt-type K-600s and K-DON 600s Circuit Breakers

```
                                                       SSINS No.: 6870  
                                                       Accession No:  
                                                       8006190040
                                                       IN 80-31 

                               UNITED STATES 
                       NUCLEAR REGULATORY COMMISSION 
                    OFFICE OF INSPECTION AND ENFORCEMENT 
                           WASHINGTON, D.C. 20555 
                                     
                              August 27, 1980 

Information Notice No. 80-31:   MALOPERATION OF GOULD-BROWN BOVERI 480 
                                   VOLT-TYPE K-600S AND K-DON 600S CIRCUIT 
                                   BREAKERS 

Description of Circumstances: 

The Cincinnati Gas & Electric Company reported problems with the Gould-Brown
Boveri Type K-600S and K-DON 600S circuit breakers used in 480 volt a.c. 
circuits at the William H. Zimmer nuclear stations. The problem involved 
inadvertent circuit breaker closure during operation of the breaker charging
springs when the breaker was racked out to the test position. 

The problem resulted from the use of undersized bushings in the circuit 
breaker secondary close latches. The undersized bushings caused the 
secondary close latch to hang-up on the shunt trip device resulting in an 
inadvertent circuit breaker closure when the spring charging motor was 
energized. 

The vendor has stated that the problem does not exist during normal 
operations with the circuit breaker in the connected position. 

Recommended Action for Licensees and Holders of Construction Permits: 

All licensees of operating nuclear power reactors and holders of 
construction permits should be aware of the potential problems described 
above. The vendor has stated that a small number of circuit breakers were 
assembled with undersized secondary latch bushings between 1969 and 1977. It 
is recommended that the following actions be taken: 

(1)  Determine if the subject circuit breakers are installed in any safety-
     related application at your facility. The affected circuit breakers are
     manufactured by Gould-Brown Boveri and are types K-600S and K-DON 600S,
     480-volt a.c. electrically operated, drawout type with static trip 
     device. 

(2)  If it is determined that your facility has the circuit breakers 
     described in Item (1) above, perform the K-600S, K-DON 6005 Field Test 
     Procedure attached to this information notice (Gould-Brown Boveri 
     I.B.-9.1.7-6 Issue F, Addendum 2, dated March 4, 1980). 

(3)  If maloperation of the circuit breaker occurs during performance of the
     field test procedure described in Item (2) above, perform the 
     corrective action described in the attached field test procedure 
     (installation of a 0.050 shim to the secondary close latch and retest 
     of the circuit breaker). 
.

                                                            IN 80-31  
                                                            August 27, 1980 
                                                            Page 2 of 2  

No written response to this information notice is required; however, if 
additional information is required, contact the Director of the appropriate 
NRC Regional Office. 

Enclosure: 
Excerpt from Gould-Brown Boveri 
  Letter to NRC Region III dated 
  June 2, 1980.
```

*Page Last Reviewed/Updated Friday, May 22, 2015*

#### Home

            - News Releases
            - Event Reports
            - ADAMS
            - Open Gov
            - Digital Government
            - The Student Corner
            - Photos & Video
            - For Developers

#### About Us

            - Strategic Plan
            - Budget & Performance
            - Agency Financial Report
            - License Fees
            - History of the NRC
            - Career Opportunities
            - NRC Ethics
            - Agency Status
            - Contact Us

#### Popular Documents

            - Info Digest
            - Fact Sheets & Brochures
            - Forms
            - Electronic Submittals Application
            - Adjudicatory Submissions
            - NRC Reports – NUREG
            - NRC Regulations – 10-CFR
            - Inspection Reports
            - Plain Writing
            - Enforcement Actions
            - RULEMAKING

#### Stay Connected

            - Blog
            - Facebook
            - Twitter
            - YouTube
            - Flickr
            - GovDelivery
            - RSS

Regulations.govUSA.govRecoveryFOIANo Fear EEOInspector General ProgramSite MapAccessibilityPrivacy PolicySite DisclaimerFor Employees