Name: Stephen Ward

Title: Senior Environmental Scientist

Company: Hawaiian Electric Company, Inc.

Sign Date:

Name: Tony Wong

Title: President

Company: AirKinetics Inc.

Sign Date: 8/30/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Emissions Testing Unit 8

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 10, 2011 Page 1 of 31
Emissions Testing Unit 8

Facility Information:

HI, Honolulu

170 Ala Moana Blv.

Honolulu HI 96813

Contact: Stephen Ward

Phone: (808) 543-4535

Fax: (808) 543-4511

Email: stephen.ward@heco.com

Testing Company:

AirKinetics Inc.

1308 S. Allec

Anaheim CA 92805

Contact:Tony Wong

Phone: (714) 245-1945

Fax: (714) 956-2350

Email: wongt@airkineticsinc.com

Air Permit Number:

0238-01-C

Permitted Source ID/Name:

8

Permitted Maximum Process Rate:

589 MMBtu/hr

Max. Normal Operation Process Rate:

619 MMBtu/hr

Target Process Test Rate

546 MMBtu/hr

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Electrical power generation though combustion of fossil fuels (SIC Code 4911) is the only product or process. “Please

 note that all information within this ERT has designated the boiler ID as Honolulu Unit 8. The Unit 8 designation is 

consistent with EPA’s designation through the Dept. of Heath and the state permit number. However, the ICR letter 

addresses the Honolulu boiler as "16" based on the EIA designation, instead of as "8". The 16 nomenclature is very 

old and cannot be changed. According to EIA guidelines, existing generator and boiler IDs cannot be changed in 

order to preserve continuity between the current reporting year data and historical data.”

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 1500300500 FRS #: 110027161568

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

stack 108 0 0 108 220 240 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

stack Carbon Monoxide Method 10 3 120 0

stack 2,3,7,8-TCDD Method 23 3 480 0

stack 1,2,3,7,8-PeCDD Method 23 3 480 0

Regulation Description Compound Limit Unit

Thursday, February 10, 2011 Page 2 of 31
Emissions Testing Unit 8

stack 1,2,3,4,7,8-HxCDD Method 23 3 480 0

stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0

stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0

stack 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

stack OCDD Method 23 3 480 0

stack 2,3,7,8-TCDF Method 23 3 480 0

stack 1,2,3,7,8-PeCDF Method 23 3 480 0

stack 2,3,4,7,8-PeCDF Method 23 3 480 0

stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0

stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0

stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0

stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0

stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

stack OCDF Method 23 3 480 0

stack Other TCDD Method 23 3 480 0

stack Other PeCDD Method 23 3 480 0

stack Other HxCDD Method 23 3 480 0

stack Other HpCDD Method 23 3 480 0

stack Other TCDF Method 23 3 480 0

stack Other PeCDF Method 23 3 480 0

stack Other HxCDF Method 23 3 480 0

stack Other HpCDF Method 23 3 480 0

stack Total Dioxins Method 23 3 480 0

stack Total Furans Method 23 3 480 0

stack 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

stack 3,4,4',5-TCB (PCB81) Method 23 3 480 0

stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

stack Method 23 3 480 0

stack 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

stack Method 23 3 480 0

stack Total TEQ Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

stack Method 25A 3 120 0

stack Hydrogen Chloride Method 26 3 60 0

stack Hydrogen Fluoride Method 26 3 60 0

stack Total Particulate OTM - 27/28 3 367 0

stack Filterable Particulate OTM - 27/28 3 367 0

Inorganic (Aqueous) 

Condensible Part.

stack OTM - 27/28 3 367 0

Organic Condensible 

Particulate

stack OTM - 27/28 3 367 0

stack Filterable PM2.5 OTM - 27/28 3 367 0

stack Total PM2.5 OTM - 27/28 3 367 0

stack Manganese Method 29 3 240 0

stack Antimony Method 29 3 240 0

Thursday, February 10, 2011 Page 3 of 31
Emissions Testing Unit 8

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None

stack Arsenic Method 29 3 240 0

stack Beryllium Method 29 3 240 0

stack Cadmium Method 29 3 240 0

stack Chromium Method 29 3 240 0

stack Lead Method 29 3 240 0

stack Nickel Method 29 3 240 0

stack Selenium Method 29 3 240 0

stack Cobalt Method 29 3 240 0

stack O2 Method 3A O2 3 120 0

stack Co2 Method 3A CO2 3 120 0

stack Filterable Particulate Method 5 3 240 0

stack Sulfur Dioxide Method 6C 3 120 0

stack Nitrogen oxides (NOx) Method 7E 3 120 0

Thursday, February 10, 2011 Page 4 of 31
Emissions Testing Unit 8

Sampling / Stack Data Results Summary

Location stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location stack - Method 23

Average

Run Number H8-M23-1 H8-M23-2 H8-M23-3

Test Date 4/16/2010 4/17/2010 7/14/2010

Run Start Time 7:25:00 AM 7:30:00 

AM

7:35:00 AM

Run Finish Time 3:48:00 PM 3:54:00 PM 4:16:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 398.340 370.876 367.944 379.053

Moisture Content of Stack Gas, % 10.80 10.94 10.85 10.863

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 12 12 12.5 12.167

Oxygen, % 5.1 5 4.5 4.867

Average Stack Gas Temperature, °F 310.71 305.88 317.25 311.280

Dry Volumetric Flow Rate, dry scfm 142,552.2 134,941.4 132,517.9 136,670.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 232,342.0 218,829.8 218,524.4 223,232.067

Percent Isokinetic of Sampling Rate, % 101.2 99.6 99.8 100.200

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 5 of 31
Emissions Testing Unit 8

Location stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location stack - Method 26

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 10, 2011 Page 6 of 31
Emissions Testing Unit 8

Location stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location stack - Method 5

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 10, 2011 Page 7 of 31
Emissions Testing Unit 8

Location stack - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location stack - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, February 10, 2011 Page 8 of 31
Emissions Testing Unit 8

Location stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 10, 2011 Page 9 of 31
Emissions Testing Unit 8

Emissions Summary

Location: stack - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 3.12E-04 4.19E-04 3.89E-04 0.000

ppm 3.59E-01 4.84E-01 4.49E-01 0.431

ppm@7%O2 3.11E-01 4.17E-01 3.87E-01 0.372

Location: stack - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.0000000269 0.00000000568 0.0000000356 0.000

lb/mmBtuO2 1.81E-12 4.08E-13 2.50E-12 0.000

ng/dscm 2.39E-03 5.41E-04 3.42E-03 0.002

ng/dscm@7%O2 2.10E-03 4.73E-04 2.90E-03 0.002

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.0000000149 0.00000000507 0.00000000994 0.000

lb/mmBtuO2 1.00E-12 3.64E-13 6.98E-13 0.000

ng/dscm 1.32E-03 4.83E-04 9.54E-04 0.001

ng/dscm@7%O2 1.16E-03 4.22E-04 8.09E-04 0.001

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.0000000062 0.00000000439 0.000000012 0.000

lb/mmBtuO2 4.17E-13 3.15E-13 8.42E-13 0.000

ng/dscm 5.50E-04 4.18E-04 1.15E-03 0.001

ng/dscm@7%O2 4.84E-04 3.65E-04 9.75E-04 0.001

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000893 0.00000000899 0.0000000282 0.000

lb/mmBtuO2 6.01E-13 6.46E-13 1.98E-12 0.000

ng/dscm 7.92E-04 8.56E-04 2.71E-03 0.001

ng/dscm@7%O2 6.97E-04 7.48E-04 2.30E-03 0.001

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000519 0.00000000349 0.00000000818 0.000

lb/mmBtuO2 3.49E-13 2.51E-13 5.74E-13 0.000

ng/dscm 4.60E-04 3.32E-04 7.85E-04 0.001

ng/dscm@7%O2 4.05E-04 2.90E-04 6.65E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

Thursday, February 10, 2011 Page 10 of 31
Emissions Testing Unit 8

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000832 0.00000000838 0.0000000263 0.000

lb/mmBtuO2 5.60E-13 6.02E-13 1.85E-12 0.000

ng/dscm 7.38E-04 7.98E-04 2.52E-03 0.001

ng/dscm@7%O2 6.49E-04 6.98E-04 2.14E-03 0.001

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000508 0.00000000328 0.00000000769 0.000

lb/mmBtuO2 3.42E-13 2.36E-13 5.40E-13 0.000

ng/dscm 4.50E-04 3.12E-04 7.38E-04 0.001

ng/dscm@7%O2 3.96E-04 2.73E-04 6.26E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000811 0.00000000816 0.0000000257 0.000

lb/mmBtuO2 5.46E-13 5.86E-13 1.80E-12 0.000

ng/dscm 7.19E-04 7.77E-04 2.47E-03 0.001

ng/dscm@7%O2 6.33E-04 6.79E-04 2.09E-03 0.001

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000457 0.00000000418 0.00000000979 0.000

lb/mmBtuO2 3.07E-13 3.00E-13 6.87E-13 0.000

ng/dscm 4.05E-04 3.98E-04 9.40E-04 0.001

ng/dscm@7%O2 3.56E-04 3.48E-04 7.97E-04 0.001

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000572 0.00000000495 0.0000000121 0.000

lb/mmBtuO2 3.85E-13 3.55E-13 8.49E-13 0.000

ng/dscm 5.07E-04 4.71E-04 1.16E-03 0.001

ng/dscm@7%O2 4.46E-04 4.12E-04 9.83E-04 0.001

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000853 0.00000000665 0.0000000116 0.000

lb/mmBtuO2 5.74E-13 4.78E-13 8.14E-13 0.000

ng/dscm 7.56E-04 6.33E-04 1.11E-03 0.001

ng/dscm@7%O2 6.65E-04 5.53E-04 9.41E-04 0.001

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.0000000247 0.00000000799 0.00000000894 0.000

lb/mmBtuO2 1.66E-12 5.74E-13 6.27E-13 0.000

ng/dscm 2.19E-03 7.61E-04 8.58E-04 0.001

ng/dscm@7%O2 1.93E-03 6.65E-04 7.27E-04 0.001

Thursday, February 10, 2011 Page 11 of 31
Emissions Testing Unit 8

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.000000878 0.0000002194 0.0000001264 0.000

lb/mmBtuO2 5.91E-11 1.58E-11 8.87E-12 0.000

ng/dscm 7.79E-02 2.09E-02 1.21E-02 0.037

ng/dscm@7%O2 6.85E-02 1.83E-02 1.03E-02 0.032

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000235 0.000000579 0.000000518 0.000

lb/mmBtuO2 1.58E-10 4.16E-11 3.63E-11 0.000

ng/dscm 2.08E-01 5.51E-02 4.97E-02 0.104

ng/dscm@7%O2 1.83E-01 4.82E-02 4.21E-02 0.091

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.000000251 0.0000000668 0.0000000513 0.000

lb/mmBtuO2 1.69E-11 4.80E-12 3.60E-12 0.000

ng/dscm 2.23E-02 6.36E-03 4.92E-03 0.011

ng/dscm@7%O2 1.96E-02 5.56E-03 4.17E-03 0.010

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.000000133 0.0000000332 0.0000000444 0.000

lb/mmBtuO2 8.95E-12 2.38E-12 3.12E-12 0.000

ng/dscm 1.18E-02 3.16E-03 4.26E-03 0.006

ng/dscm@7%O2 1.04E-02 2.76E-03 3.61E-03 0.006

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000546 0.00000147 0.00000129 0.000

lb/mmBtuO2 3.67E-10 1.06E-10 9.05E-11 0.000

ng/dscm 4.84E-01 1.40E-01 1.24E-01 0.249

ng/dscm@7%O2 4.26E-01 1.22E-01 1.05E-01 0.218

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.0000000814 0.0000000297 0.0000000411 0.000

lb/mmBtuO2 5.48E-12 2.13E-12 2.88E-12 0.000

ng/dscm 7.22E-03 2.83E-03 3.95E-03 0.005

ng/dscm@7%O2 6.35E-03 2.47E-03 3.35E-03 0.004

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000389 0.00000000355 0.00000000833 0.000

lb/mmBtuO2 2.62E-13 2.55E-13 5.85E-13 0.000

Thursday, February 10, 2011 Page 12 of 31
Emissions Testing Unit 8

ng/dscm 3.45E-04 3.38E-04 8.00E-04 0.000

ng/dscm@7%O2 3.04E-04 2.95E-04 6.78E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000881 0.00000000687 0.000000012 0.000

lb/mmBtuO2 5.93E-13 4.93E-13 8.42E-13 0.000

ng/dscm 7.81E-04 6.54E-04 1.15E-03 0.001

ng/dscm@7%O2 6.87E-04 5.72E-04 9.75E-04 0.001

Compound: 2,3,7,8-TCDD

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000482 0.00000000468 0.00000000967 0.000

lb/mmBtuO2 3.24E-13 3.36E-13 6.79E-13 0.000

ng/dscm 4.27E-04 4.46E-04 9.28E-04 0.001

ng/dscm@7%O2 3.76E-04 3.90E-04 7.87E-04 0.001

Compound: 2,3,7,8-TCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000596 0.00000000816 0.00000000926 0.000

lb/mmBtuO2 4.01E-13 5.86E-13 6.50E-13 0.000

ng/dscm 5.28E-04 7.77E-04 8.89E-04 0.001

ng/dscm@7%O2 4.65E-04 6.79E-04 7.53E-04 0.001

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000169 0.00000000301 0.0000000177 0.000

lb/mmBtuO2 1.14E-13 2.16E-13 1.24E-12 0.000

ng/dscm 1.50E-04 2.87E-04 1.70E-03 0.001

ng/dscm@7%O2 1.32E-04 2.51E-04 1.44E-03 0.001

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.0000000386 0.0000000116 0.0000000364 0.000

lb/mmBtuO2 2.60E-12 8.33E-13 2.55E-12 0.000

ng/dscm 3.42E-03 1.10E-03 3.49E-03 0.003

ng/dscm@7%O2 3.01E-03 9.62E-04 2.96E-03 0.002

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.0000000597 0.0000000676 0.0000000203 0.000

lb/mmBtuO2 4.02E-12 4.85E-12 1.42E-12 0.000

ng/dscm 5.29E-03 6.44E-03 1.95E-03 0.005

ng/dscm@7%O2 4.65E-03 5.63E-03 1.65E-03 0.004

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Thursday, February 10, 2011 Page 13 of 31
Emissions Testing Unit 8

Mass_mg 0.0000000729 0.0000000234 0.0000000365 0.000

lb/mmBtuO2 4.90E-12 1.68E-12 2.56E-12 0.000

ng/dscm 6.46E-03 2.23E-03 3.50E-03 0.004

ng/dscm@7%O2 5.68E-03 1.95E-03 2.97E-03 0.004

Compound: OCDD

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.000000154 0.0000000215 0.0000000548 0.000

lb/mmBtuO2 1.04E-11 1.54E-12 3.85E-12 0.000

ng/dscm 1.37E-02 2.05E-03 5.26E-03 0.007

ng/dscm@7%O2 1.21E-02 1.79E-03 4.46E-03 0.006

Compound: OCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.0000000105 0.00000000804 0.0000000233 0.000

lb/mmBtuO2 7.06E-13 5.77E-13 1.64E-12 0.000

ng/dscm 9.31E-04 7.66E-04 2.24E-03 0.001

ng/dscm@7%O2 8.19E-04 6.70E-04 1.90E-03 0.001

Compound: Other HpCDD

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0 0.00000000167 0 0.000

lb/mmBtuO2 0.00E+00 1.20E-13 0.00E+00 0.000

ng/dscm 0.00E+00 1.59E-04 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 1.39E-04 0.00E+00 0.000

Compound: Other HpCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDD

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000327 0 0 0.000

lb/mmBtuO2 2.20E-13 0.00E+00 0.00E+00 0.000

ng/dscm 2.90E-04 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 2.55E-04 0.00E+00 0.00E+00 0.000

Thursday, February 10, 2011 Page 14 of 31
Emissions Testing Unit 8

Compound: Other PeCDD

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.0000000004 0.00000000002 0 0.000

lb/mmBtuO2 2.69E-14 1.44E-15 0.00E+00 0.000

ng/dscm 3.55E-05 1.90E-06 0.00E+00 0.000

ng/dscm@7%O2 3.12E-05 1.66E-06 0.00E+00 0.000

Compound: Other PeCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other TCDD

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000558 0 0.00000000002 0.000

lb/mmBtuO2 3.75E-13 0.00E+00 1.40E-15 0.000

ng/dscm 4.95E-04 0.00E+00 1.92E-06 0.000

ng/dscm@7%O2 4.35E-04 0.00E+00 1.63E-06 0.000

Compound: Other TCDF

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000000164 0 0.00000000001 0.000

lb/mmBtuO2 1.10E-13 0.00E+00 7.02E-16 0.000

ng/dscm 1.45E-04 0.00E+00 9.60E-07 0.000

ng/dscm@7%O2 1.28E-04 0.00E+00 8.14E-07 0.000

Compound: Total Dioxins

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.000000202 0.000000047 0.000000139 0.000

lb/mmBtuO2 1.36E-11 3.37E-12 9.75E-12 0.000

ng/dscm 1.79E-02 4.48E-03 1.33E-02 0.012

ng/dscm@7%O2 1.57E-02 3.92E-03 1.13E-02 0.010

Compound: Total Furans

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.000000069 0.000000035 0.000000063 0.000

lb/mmBtuO2 4.64E-12 2.51E-12 4.42E-12 0.000

ng/dscm 6.12E-03 3.33E-03 6.05E-03 0.005

ng/dscm@7%O2 5.38E-03 2.91E-03 5.13E-03 0.004

Compound: Total TEQ

Average

RunNumber H8-M23-1 H8-M23-2 H8-M23-3

Mass_mg 0.00000001816 0.00000001592 0.0000000353 0.000

lb/mmBtuO2 1.22E-12 1.14E-12 2.48E-12 0.000

Thursday, February 10, 2011 Page 15 of 31
Emissions Testing Unit 8

ng/dscm 1.61E-03 1.52E-03 3.39E-03 0.002

ng/dscm@7%O2 1.42E-03 1.33E-03 2.87E-03 0.002

Location: stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 1.00E-03 8.44E-04 2.15E-03 0.001

ppm 7.32E-01 6.19E-01 1.58E+00 0.977

ppm@7%O2 6.34E-01 5.34E-01 1.36E+00 0.843

Location: stack - Method 26

Compound: Hydrogen Chloride

Average

RunNumber H8-M26-1 H8-M26-2 H8-M26-3

Mass_mg 1.263 1.077 0.828 1.056

lb/mmBtuO2 9.35E-04 7.60E-04 6.09E-04 0.001

Compound: Hydrogen Fluoride

Average

RunNumber H8-M26-1 H8-M26-2 H8-M26-3

Mass_mg 0.212 0.22 0.208 0.213

lb/mmBtuO2 1.57E-04 1.55E-04 1.53E-04 0.000

Location: stack - Method 29

Compound: Antimony

Average

RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4

Mass_mg 0.002181 0.008204 0.005836 0.005

lb/mmBtuO2 3.03E-07 1.15E-06 8.12E-07 0.000

Compound: Arsenic

Average

RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4

Mass_mg 0.0178 0.02055 0.01782 0.019

lb/mmBtuO2 2.47E-06 2.89E-06 2.48E-06 0.000

Compound: Beryllium

Average

RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4

Mass_mg 0.00135 0.00215 0.00165 0.002

lb/mmBtuO2 1.88E-07 3.02E-07 2.30E-07 0.000

Compound: Cadmium

Average

RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4

Mass_mg 0.000371 0.00077 0.000722 0.001

lb/mmBtuO2 5.16E-08 1.08E-07 1.00E-07 0.000

Compound: Chromium

Average

RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4

Thursday, February 10, 2011 Page 16 of 31
Emissions Testing Unit 8

Mass_mg 0.009519 0.01799 0.01639 0.015

lb/mmBtuO2 1.32E-06 2.53E-06 2.28E-06 0.000

Compound: Cobalt

Average

RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4

Mass_mg 0.16095 0.2797 0.26182 0.234

lb/mmBtuO2 2.24E-05 3.93E-05 3.64E-05 0.000

Compound: Lead

Average

RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4

Mass_mg 0.004418 0.104 0.021812 0.043

lb/mmBtuO2 6.14E-07 1.46E-05 3.04E-06 0.000

Compound: Manganese

Average

RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4

Mass_mg 0.09386 0.08518 0.06652 0.082

lb/mmBtuO2 1.30E-05 1.20E-05 9.26E-06 0.000

Compound: Nickel

Average

RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4

Mass_mg 3.87007 6.79537 6.34017 5.669

lb/mmBtuO2 5.38E-04 9.55E-04 8.82E-04 0.001

Compound: Selenium

Average

RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4

Mass_mg 0.01192 0.00762 0.00662 0.009

lb/mmBtuO2 1.66E-06 1.07E-06 9.21E-07 0.000

Location: stack - Method 5

Compound: Filterable Particulate

Average

RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4

Mass_mg 89.7 251.3 145 162.000

lb/mmBtuO2 1.25E-02 3.53E-02 2.02E-02 0.023

Location: stack - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 3.69E-01 3.65E-01 3.64E-01 0.366

ppm 1.86E+02 1.84E+02 1.84E+02 184.667

ppm@7%O2 1.61E+02 1.59E+02 1.58E+02 159.333

Location: stack - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

Thursday, February 10, 2011 Page 17 of 31
Emissions Testing Unit 8

Process Run Data

lb/mmBtuO2 5.55E-01 5.54E-01 5.59E-01 0.556

ppm 3.89E+02 3.89E+02 3.94E+02 390.667

ppm@7%O2 3.37E+02 3.35E+02 3.39E+02 337.000

Location: stack - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber H8-OTM27/28-2 H8-OTM27/28-3 H8-OTM27/28-4

Mass_mg 154.1 107.2 105.4 122.233

lb/mmBtuO2 3.22E-02 2.04E-02 2.18E-02 0.025

Compound: Filterable PM2.5

Average

RunNumber H8-OTM27/28-2 H8-OTM27/28-3 H8-OTM27/28-4

Mass_mg 69 68.4 63.6 67.000

lb/mmBtuO2 1.44E-02 1.30E-02 1.31E-02 0.014

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber H8-OTM27/28-2 H8-OTM27/28-3 H8-OTM27/28-4

Mass_mg 13.6 14.4 14.6 14.200

lb/mmBtuO2 2.84E-03 2.74E-03 3.02E-03 0.003

Compound: Organic Condensible Particulate

Average

RunNumber H8-OTM27/28-2 H8-OTM27/28-3 H8-OTM27/28-4

Mass_mg 1.3 0.4 1.9 1.200

lb/mmBtuO2 2.71E-04 7.62E-05 3.93E-04 0.000

Compound: Total Particulate

Average

RunNumber H8-OTM27/28-2 H8-OTM27/28-3 H8-OTM27/28-4

Mass_mg 167 120 119.9 135.633

lb/mmBtuO2 3.49E-02 2.29E-02 2.48E-02 0.028

Compound: Total PM2.5

Average

RunNumber H8-OTM27/28-2 H8-OTM27/28-3 H8-OTM27/28-4

Mass_mg 81.9 81.2 78.1 80.400

lb/mmBtuO2 1.71E-02 1.55E-02 1.61E-02 0.016

Thursday, February 10, 2011 Page 18 of 31
Emissions Testing Unit 8

Process Run Data

Run Name Value UOM Comments

Target

Value

1 0

2 0

1 0

2 0

1 0

2 0

1 0

2 0

1 0

2 0

1 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

2 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

1 0

1 Unit Gross Electric Generation 52.83 Mwe

1 Unit Net Electric Generation 49.84 MWh

1 Steam Output 430.631,000 lbs steam/hr EPA Method 30B 

Run H8-M30B-1

1 Average Heat Input 557.82 MMBtu/hr EPA Method 23 

Run H8-M23-1

1 Fuel Oil Firing Rate 29.39 Klb/hr April 16, 2010 

Test Day

3 0

3 0

3 0

3 0

3 0

3 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

3 0

3 Unit Gross Electric Generation 51.53 Mwe

3 Unit Net Electric Generation 48.61 MWh

3 Steam Output 419.281,000 lbs steam/hr EPA Method 23 

Run H8-M23-2

3 Average Heat Input 543.47 MMBtu/hr EPA Method 5/29 

Run H8-M5/29-2

3 Fuel Oil Firing Rate 28.53 Klb/hr April 17, 2010 

Test Day

Thursday, February 10, 2011 Page 19 of 31
Emissions Testing Unit 8

4 0

4 0

4 0

4 0

4 0 EPA Method 18: 

Runs H8-M18-1, 

H8-M18-2, H8-

M18-3

4 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

4 0 EPA Method 

0031/SW-846 

8260B Runs H8-

M0031-1, H8-

M0031-2, and H8-

M0031-3

4 Unit Gross Electric Generation 51.92 Mwe EPA Method 

0010/SW-846 

8270D Runs H8-

M0010-1, H8-

M0010-2, and H8-

M0010-2

4 Unit Net Electric Generation 49.06 MWh EPA Method 316 

Runs H8-M316-1, 

H8-M316-2, and 

H8-M316-3

4 Steam Output 420.871,000 lbs steam/hr EPA Method 

26/CTM-033 Runs 

H8-M26-1, H8-

M26-2, and H8-

M26-3

4 Average Heat Input 547.62 MMBtu/hr EPA Method 3A, 

6C, 7E, 10, and 

25A Runs 1, 2, 

and 3

4 Fuel Oil Firing Rate 28.93 Klb/hr April 19, 2010 

Test Day

5 0

5 0

5 0

5 0

5 0

5 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

5 0

5 Unit Gross Electric Generation 52.38 Mwe

Thursday, February 10, 2011 Page 20 of 31
Emissions Testing Unit 8

5 Unit Net Electric Generation 49.43 MWh EPA Method 

OTM 27/28 Run 

H8-OTM27/28-2

5 Steam Output 433.671,000 lbs steam/hr EPA Method 30B 

Run H8-M30B-2

5 Average Heat Input 548.12 MMBtu/hr EPA Method 5/29 

Run H8-M5/29-3

5 Fuel Oil Firing Rate 29.45 Klb/hr July 13, 2010 Test 

Day

6 0

6 0

6 0

6 0

6 0

6 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

6 0

6 Unit Gross Electric Generation 52.76 Mwe EPA Method 

OTM 27/28 Run 

H8-OTM27/28-3

6 Unit Net Electric Generation 49.81 MWh EPA Method 30B 

Run H8-M30B-3

6 Steam Output 436.371,000 lbs steam/hr EPA Method 23 

Run H8-M23-3

6 Average Heat Input 550.24 MMBtu/hr EPA Method 5/29 

Run H8-M5/29-4

6 Fuel Oil Firing Rate 29.58 Klb/hr July 14, 2010 Test 

Day

7 0

7 0

7 0

7 0

7 0

7 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

7 0

7 Unit Gross Electric Generation 51.82 Mwe

7 Unit Net Electric Generation 48.86 MWh

7 Steam Output 428.591,000 lbs steam/hr

7 Average Heat Input 543.47 MMBtu/hr EPA Method 

OTM 27/28 Run 

H8-OTM27/28-4

7 Fuel Oil Firing Rate 28.99 Klb/hr July 15, 2010 Test 

Day

Thursday, February 10, 2011 Page 21 of 31
Emissions Testing Unit 8

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 None 0

1 0

1 0

1 0

Run Name Value UOM Comments

1 none 0

1 0

1 0

1 0

1 0

Thursday, February 10, 2011 Page 22 of 31
Emissions Testing Unit 8

Sampling / Stack Data Results Detail

Location stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 10, 2011 Page 23 of 31
Emissions Testing Unit 8

Location stack - Method 23

Average

Run Number H8-M23-1 H8-M23-2 H8-M23-3

Test Date 4/16/2010 4/17/2010 7/14/2010

Run Start Time 7:25:00 AM 7:30:00 AM 7:35:00 AM

Run Finish Time 3:48:00 PM 3:54:00 PM 4:16:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.259 0.259 0.26 0.259

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.02 1.02 1.03 1.023

Barometric Pressure, inches of Mercury 30.1 30.1 30 30.067

Average Orifice Meter Differential, inches H2O 2.53 2.27 2.40 2.400

Dry Gas Meter Volume Sampled, cubic feet 397.303 371.023 373.490 380.605

Average Dry Gas Meter Temperature, °F 83.73 85.02 96.77 88.507

Dry Gas Meter Volume Sampled, dscf 398.340 370.876 367.944 379.053

Total Moisture Liquid collected, g 1024.3 967.6 951.4 981.100

Volume of Water Vapor, standard cubic feet 48.21 45.54 44.78 46.177

Moisture Content of Stack Gas, % 10.80 10.94 10.85 10.863

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.892 0.8906 0.8915 0.891

Carbon Dioxide, % 12 12 12.5 12.167

Oxygen, % 5.1 5 4.5 4.867

Carbon Monoxide & Nitrogen, % 82.9 83 83 82.967

Fuel Factor 1.32 1.33 1.31

Dry Molecular Weight, lb/lb-Mole 30.12 30.12 30.18 30.140

Wet Molecular weight, lb/lb-Mole 28.81 28.79 28.86 28.820

Flue Gas Static Pressure, inches of H2O -0.81 -0.68 -0.55 -0.680

Absolute Flue Gas Pressure, inches of Mercury 30.04 30.05 29.96 30.017

Average Stack Gas Temperature, °F 310.71 305.88 317.25 311.280

Average Velocity Head, inches of H2O 0.8068813315

574

0.719943260

182994

0.706937852

158604

0.745

Average Stack Gas Velocity, feet/second 60.87 57.33 57.25 58.483

Stack Cross-Sectional Area, square feet 63.617 63.617 63.617 63.617

Dry Volumetric Flow Rate, dry scfm 142,552.2 134,941.4 132,517.9 136,670.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 232,342.0 218,829.8 218,524.4 223,232.067

Percent Isokinetic of Sampling Rate, % 101.2 99.6 99.8 100.200

Percent Excess Air, % 30.4 29.6 25.8 28.600

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 108 108 108

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 24 of 31
Emissions Testing Unit 8

Location stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 10, 2011 Page 25 of 31
Emissions Testing Unit 8

Location stack - Method 26

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 10, 2011 Page 26 of 31
Emissions Testing Unit 8

Location stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 10, 2011 Page 27 of 31
Emissions Testing Unit 8

Location stack - Method 5

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 10, 2011 Page 28 of 31
Emissions Testing Unit 8

Location stack - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 10, 2011 Page 29 of 31
Emissions Testing Unit 8

Location stack - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 10, 2011 Page 30 of 31
Emissions Testing Unit 8

Location stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 10, 2011 Page 31 of 31