### Name: Stephen Ward

Title: Senior Environmental Scientist Company: Hawaiian Electric Company, Inc. Sign Date: Name: Tony Wong Title: President Company: AirKinetics Inc. Sign Date: 8/30/2010 Permitted Facility Representative / Date Testing Company Representative / Date 

## Emissions Testing Unit 8 Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Thursday, February 10, 2011 Page 1 of 31

### Emissions Testing Unit 8

Facility Information: HI, Honolulu
170 Ala Moana Blv.

Honolulu HI 96813 Contact: Stephen Ward Phone: (808) 543-4535 Fax: (808) 543-4511 Email: stephen.ward@heco.com Testing Company:
AirKinetics Inc.
1308 S. Allec

Anaheim CA 92805 Contact: Tony Wong Phone: (714) 245-1945 Fax: (714) 956-2350 Email: wongt@airkineticsinc.com

Air Permit Number: 0238-01-C Permitted Source ID/Name: 8 Permitted Maximum Process Rate: 589 MMBtu/hr Max. Normal Operation Process Rate: 619 MMBtu/hr Target Process Test Rate 546 MMBtu/hr

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Electrical power generation though combustion of fossil fuels (SIC Code 4911) is the only product or process. “Please note that all information within this ERT has designated the boiler ID as Honolulu Unit 8. The Unit 8 designation is consistent with EPA’s designation through the Dept. of Heath and the state permit number. However, the ICR letter addresses the Honolulu boiler as "16" based on the EIA designation, instead of as "8". The 16 nomenclature is very old and cannot be changed. According to EIA guidelines, existing generator and boiler IDs cannot be changed in order to preserve continuity between the current reporting year data and historical data.” Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information: AFS #: 1500300500 FRS #: 110027161568

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: Normal Firing

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width stack 108 220 240 4 108 12 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location Carbon Monoxide Method 10 3 120 0 stack 2,3,7,8-TCDD Method 23 3 480 0 stack 1,2,3,7,8-PeCDD Method 23 3 480 0 stack Regulation Description Compound Limit Unit



### Thursday, February 10, 2011 Page 2 of 31

### Emissions Testing Unit 8

1,2,3,4,7,8-HxCDD Method 23 3 480 0 stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0 stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0 stack 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0 stack OCDD Method 23 3 480 0 stack 2,3,7,8-TCDF Method 23 3 480 0 stack 1,2,3,7,8-PeCDF Method 23 3 480 0 stack 2,3,4,7,8-PeCDF Method 23 3 480 0 stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0 stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0 stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0 stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0 stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0 stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0 stack OCDF Method 23 3 480 0 stack Other TCDD Method 23 3 480 0 stack Other PeCDD Method 23 3 480 0 stack Other HxCDD Method 23 3 480 0 stack Other HpCDD Method 23 3 480 0 stack Other TCDF Method 23 3 480 0 stack Other PeCDF Method 23 3 480 0 stack Other HxCDF Method 23 3 480 0 stack Other HpCDF Method 23 3 480 0 stack Total Dioxins Method 23 3 480 0 stack Total Furans Method 23 3 480 0 stack 3,3',4,4'-TCB (PCB77) Method 23 3 480 0 stack 3,4,4',5-TCB (PCB81) Method 23 3 480 0 stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0 stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0 stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0 stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0 stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0 stack 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 480 0 stack

2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0 stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0 stack 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 480 0 stack

Total TEQ Method 23 3 480 0 stack Total organic compounds

(TOC) as Propane Method 25A 3 120 0 stack
Hydrogen Chloride Method 26 3 60 0 stack Hydrogen Fluoride Method 26 3 60 0 stack Total Particulate OTM - 27/28 3 367 0 stack Filterable Particulate OTM - 27/28 3 367 0 stack Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 367 0 stack
Organic Condensible

Particulate OTM - 27/28 3 367 0 stack

Filterable PM2.5 OTM - 27/28 3 367 0 stack Total PM2.5 OTM - 27/28 3 367 0 stack Manganese Method 29 3 240 0 stack Antimony Method 29 3 240 0 stack



### Thursday, February 10, 2011 Page 3 of 31

### Emissions Testing Unit 8

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.
None Arsenic Method 29 3 240 0 stack Beryllium Method 29 3 240 0 stack Cadmium Method 29 3 240 0 stack Chromium Method 29 3 240 0 stack Lead Method 29 3 240 0 stack Nickel Method 29 3 240 0 stack Selenium Method 29 3 240 0 stack Cobalt Method 29 3 240 0 stack O2 Method 3A O2 3 120 0 stack Co2 Method 3A CO2 3 120 0 stack Filterable Particulate Method 5 3 240 0 stack Sulfur Dioxide Method 6C 3 120 0 stack Nitrogen oxides (NOx) Method 7E 3 120 0 stack



### Thursday, February 10, 2011 Page 4 of 31

### Emissions Testing Unit 8

Sampling / Stack Data Results Summary



### Location stack - Method 10 Average Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location stack - Method 23 Average Run Number H8-M23-1 H8-M23-2 H8-M23-3
Test Date 4/16/2010 4/17/2010 7/14/2010 Run Start Time 7:25:00 AM 7:30:00 AM 7:35:00 AM

Run Finish Time 3:48:00 PM 3:54:00 PM 4:16:00 PM Net Run Time, minutes 480 480 480 Dry Gas Meter Volume Sampled, dscf 398.340 370.876 367.944 379.053 Moisture Content of Stack Gas, % 10.80 10.94 10.85 10.863 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 12 12 12.5 12.167 Oxygen, % 5.1 5 4.5 4.867 Average Stack Gas Temperature, °F 310.71 305.88 317.25 311.280 Dry Volumetric Flow Rate, dry scfm 142,552.2 134,941.4 132,517.9 136,670.500 Actual Wet Volumetric Flue Gas Flow Rate, acfm 232,342.0 218,829.8 218,524.4 223,232.067 Percent Isokinetic of Sampling Rate, % 101.2 99.6 99.8 100.200 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Thursday, February 10, 2011 Page 5 of 31

### Emissions Testing Unit 8

Location stack - Method 25A Average Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location stack - Method 26 Average Run Number
Test Date Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Thursday, February 10, 2011 Page 6 of 31

### Emissions Testing Unit 8

Location stack - Method 29 Average Run Number
Test Date Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Location stack - Method 5 Average Run Number
Test Date Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Thursday, February 10, 2011 Page 7 of 31

### Emissions Testing Unit 8

Location stack - Method 6C Average Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location stack - Method 7E Average Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Thursday, February 10, 2011 Page 8 of 31

### Emissions Testing Unit 8

Location stack - OTM - 27/28 Average Run Number
Test Date Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Thursday, February 10, 2011 Page 9 of 31

### Emissions Testing Unit 8

Emissions Summary



### Location: stack - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 lb/mmBtuO2 3.12E-04 4.19E-04 3.89E-04 0.000 ppm 3.59E-01 4.84E-01 4.49E-01 0.431 ppm@7%O2 3.11E-01 4.17E-01 3.87E-01 0.372



### Location: stack - Method 23 Compound: 1,2,3,4,6,7,8-HpCDD Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.0000000269 0.00000000568 0.0000000356 0.000 lb/mmBtuO2 1.81E-12 4.08E-13 2.50E-12 0.000 ng/dscm 2.39E-03 5.41E-04 3.42E-03 0.002 ng/dscm@7%O2 2.10E-03 4.73E-04 2.90E-03 0.002 

### Compound: 1,2,3,4,6,7,8-HpCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.0000000149 0.00000000507 0.00000000994 0.000 lb/mmBtuO2 1.00E-12 3.64E-13 6.98E-13 0.000 ng/dscm 1.32E-03 4.83E-04 9.54E-04 0.001 ng/dscm@7%O2 1.16E-03 4.22E-04 8.09E-04 0.001 

### Compound: 1,2,3,4,7,8,9-HpCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.0000000062 0.00000000439 0.000000012 0.000 lb/mmBtuO2 4.17E-13 3.15E-13 8.42E-13 0.000 ng/dscm 5.50E-04 4.18E-04 1.15E-03 0.001 ng/dscm@7%O2 4.84E-04 3.65E-04 9.75E-04 0.001 

### Compound: 1,2,3,4,7,8-HxCDD Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000893 0.00000000899 0.0000000282 0.000 lb/mmBtuO2 6.01E-13 6.46E-13 1.98E-12 0.000 ng/dscm 7.92E-04 8.56E-04 2.71E-03 0.001 ng/dscm@7%O2 6.97E-04 7.48E-04 2.30E-03 0.001 

### Compound: 1,2,3,4,7,8-HxCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000519 0.00000000349 0.00000000818 0.000 lb/mmBtuO2 3.49E-13 2.51E-13 5.74E-13 0.000 ng/dscm 4.60E-04 3.32E-04 7.85E-04 0.001 ng/dscm@7%O2 4.05E-04 2.90E-04 6.65E-04 0.000 

### Compound: 1,2,3,6,7,8-HxCDD Average


### Thursday, February 10, 2011 Page 10 of 31

### Emissions Testing Unit 8

RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000832 0.00000000838 0.0000000263 0.000 lb/mmBtuO2 5.60E-13 6.02E-13 1.85E-12 0.000 ng/dscm 7.38E-04 7.98E-04 2.52E-03 0.001 ng/dscm@7%O2 6.49E-04 6.98E-04 2.14E-03 0.001 

### Compound: 1,2,3,6,7,8-HxCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000508 0.00000000328 0.00000000769 0.000 lb/mmBtuO2 3.42E-13 2.36E-13 5.40E-13 0.000 ng/dscm 4.50E-04 3.12E-04 7.38E-04 0.001 ng/dscm@7%O2 3.96E-04 2.73E-04 6.26E-04 0.000 

### Compound: 1,2,3,7,8,9-HxCDD Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000811 0.00000000816 0.0000000257 0.000 lb/mmBtuO2 5.46E-13 5.86E-13 1.80E-12 0.000 ng/dscm 7.19E-04 7.77E-04 2.47E-03 0.001 ng/dscm@7%O2 6.33E-04 6.79E-04 2.09E-03 0.001 

### Compound: 1,2,3,7,8,9-HxCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000457 0.00000000418 0.00000000979 0.000 lb/mmBtuO2 3.07E-13 3.00E-13 6.87E-13 0.000 ng/dscm 4.05E-04 3.98E-04 9.40E-04 0.001 ng/dscm@7%O2 3.56E-04 3.48E-04 7.97E-04 0.001 

### Compound: 1,2,3,7,8-PeCDD Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000572 0.00000000495 0.0000000121 0.000 lb/mmBtuO2 3.85E-13 3.55E-13 8.49E-13 0.000 ng/dscm 5.07E-04 4.71E-04 1.16E-03 0.001 ng/dscm@7%O2 4.46E-04 4.12E-04 9.83E-04 0.001 

### Compound: 1,2,3,7,8-PeCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000853 0.00000000665 0.0000000116 0.000 lb/mmBtuO2 5.74E-13 4.78E-13 8.14E-13 0.000 ng/dscm 7.56E-04 6.33E-04 1.11E-03 0.001 ng/dscm@7%O2 6.65E-04 5.53E-04 9.41E-04 0.001 

### Compound: 2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.0000000247 0.00000000799 0.00000000894 0.000 lb/mmBtuO2 1.66E-12 5.74E-13 6.27E-13 0.000 ng/dscm 2.19E-03 7.61E-04 8.58E-04 0.001 ng/dscm@7%O2 1.93E-03 6.65E-04 7.27E-04 0.001



### Thursday, February 10, 2011 Page 11 of 31

### Emissions Testing Unit 8

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.000000878 0.0000002194 0.0000001264 0.000 lb/mmBtuO2 5.91E-11 1.58E-11 8.87E-12 0.000 ng/dscm 7.79E-02 2.09E-02 1.21E-02 0.037 ng/dscm@7%O2 6.85E-02 1.83E-02 1.03E-02 0.032 

### Compound: 2,3,3',4,4'-PeCB (PCB105) Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000235 0.000000579 0.000000518 0.000 lb/mmBtuO2 1.58E-10 4.16E-11 3.63E-11 0.000 ng/dscm 2.08E-01 5.51E-02 4.97E-02 0.104 ng/dscm@7%O2 1.83E-01 4.82E-02 4.21E-02 0.091 

### Compound: 2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.000000251 0.0000000668 0.0000000513 0.000 lb/mmBtuO2 1.69E-11 4.80E-12 3.60E-12 0.000 ng/dscm 2.23E-02 6.36E-03 4.92E-03 0.011 ng/dscm@7%O2 1.96E-02 5.56E-03 4.17E-03 0.010 

### Compound: 2,3,4,4',5-PeCB (PCB114) Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.000000133 0.0000000332 0.0000000444 0.000 lb/mmBtuO2 8.95E-12 2.38E-12 3.12E-12 0.000 ng/dscm 1.18E-02 3.16E-03 4.26E-03 0.006 ng/dscm@7%O2 1.04E-02 2.76E-03 3.61E-03 0.006 

### Compound: 2,3',4,4',5-PeCB (PCB118) Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000546 0.00000147 0.00000129 0.000 lb/mmBtuO2 3.67E-10 1.06E-10 9.05E-11 0.000 ng/dscm 4.84E-01 1.40E-01 1.24E-01 0.249 ng/dscm@7%O2 4.26E-01 1.22E-01 1.05E-01 0.218 

### Compound: 2',3,4,4',5-PeCB (PCB123) Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.0000000814 0.0000000297 0.0000000411 0.000 lb/mmBtuO2 5.48E-12 2.13E-12 2.88E-12 0.000 ng/dscm 7.22E-03 2.83E-03 3.95E-03 0.005 ng/dscm@7%O2 6.35E-03 2.47E-03 3.35E-03 0.004 

### Compound: 2,3,4,6,7,8-HxCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000389 0.00000000355 0.00000000833 0.000 lb/mmBtuO2 2.62E-13 2.55E-13 5.85E-13 0.000



### Thursday, February 10, 2011 Page 12 of 31

### Emissions Testing Unit 8

ng/dscm 3.45E-04 3.38E-04 8.00E-04 0.000 ng/dscm@7%O2 3.04E-04 2.95E-04 6.78E-04 0.000 

### Compound: 2,3,4,7,8-PeCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000881 0.00000000687 0.000000012 0.000 lb/mmBtuO2 5.93E-13 4.93E-13 8.42E-13 0.000 ng/dscm 7.81E-04 6.54E-04 1.15E-03 0.001 ng/dscm@7%O2 6.87E-04 5.72E-04 9.75E-04 0.001 

### Compound: 2,3,7,8-TCDD Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000482 0.00000000468 0.00000000967 0.000 lb/mmBtuO2 3.24E-13 3.36E-13 6.79E-13 0.000 ng/dscm 4.27E-04 4.46E-04 9.28E-04 0.001 ng/dscm@7%O2 3.76E-04 3.90E-04 7.87E-04 0.001 

### Compound: 2,3,7,8-TCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000596 0.00000000816 0.00000000926 0.000 lb/mmBtuO2 4.01E-13 5.86E-13 6.50E-13 0.000 ng/dscm 5.28E-04 7.77E-04 8.89E-04 0.001 ng/dscm@7%O2 4.65E-04 6.79E-04 7.53E-04 0.001 

### Compound: 3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000169 0.00000000301 0.0000000177 0.000 lb/mmBtuO2 1.14E-13 2.16E-13 1.24E-12 0.000 ng/dscm 1.50E-04 2.87E-04 1.70E-03 0.001 ng/dscm@7%O2 1.32E-04 2.51E-04 1.44E-03 0.001 

### Compound: 3,3',4,4',5-PeCB (PCB126) Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.0000000386 0.0000000116 0.0000000364 0.000 lb/mmBtuO2 2.60E-12 8.33E-13 2.55E-12 0.000 ng/dscm 3.42E-03 1.10E-03 3.49E-03 0.003 ng/dscm@7%O2 3.01E-03 9.62E-04 2.96E-03 0.002 

### Compound: 3,3',4,4'-TCB (PCB77) Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.0000000597 0.0000000676 0.0000000203 0.000 lb/mmBtuO2 4.02E-12 4.85E-12 1.42E-12 0.000 ng/dscm 5.29E-03 6.44E-03 1.95E-03 0.005 ng/dscm@7%O2 4.65E-03 5.63E-03 1.65E-03 0.004 

### Compound: 3,4,4',5-TCB (PCB81) Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3


### Thursday, February 10, 2011 Page 13 of 31

### Emissions Testing Unit 8

Mass_mg 0.0000000729 0.0000000234 0.0000000365 0.000 lb/mmBtuO2 4.90E-12 1.68E-12 2.56E-12 0.000 ng/dscm 6.46E-03 2.23E-03 3.50E-03 0.004 ng/dscm@7%O2 5.68E-03 1.95E-03 2.97E-03 0.004 

### Compound: OCDD Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.000000154 0.0000000215 0.0000000548 0.000 lb/mmBtuO2 1.04E-11 1.54E-12 3.85E-12 0.000 ng/dscm 1.37E-02 2.05E-03 5.26E-03 0.007 ng/dscm@7%O2 1.21E-02 1.79E-03 4.46E-03 0.006 

### Compound: OCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.0000000105 0.00000000804 0.0000000233 0.000 lb/mmBtuO2 7.06E-13 5.77E-13 1.64E-12 0.000 ng/dscm 9.31E-04 7.66E-04 2.24E-03 0.001 ng/dscm@7%O2 8.19E-04 6.70E-04 1.90E-03 0.001 

### Compound: Other HpCDD Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0 0.00000000167 0 0.000 lb/mmBtuO2 0.00E+00 1.20E-13 0.00E+00 0.000 ng/dscm 0.00E+00 1.59E-04 0.00E+00 0.000 ng/dscm@7%O2 0.00E+00 1.39E-04 0.00E+00 0.000 

### Compound: Other HpCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0 0 0 0.000 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000 

### Compound: Other HxCDD Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0 0 0 0.000 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000 

### Compound: Other HxCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000327 0 0 0.000 lb/mmBtuO2 2.20E-13 0.00E+00 0.00E+00 0.000 ng/dscm 2.90E-04 0.00E+00 0.00E+00 0.000 ng/dscm@7%O2 2.55E-04 0.00E+00 0.00E+00 0.000



### Thursday, February 10, 2011 Page 14 of 31

### Emissions Testing Unit 8

Compound: Other PeCDD Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.0000000004 0.00000000002 0 0.000 lb/mmBtuO2 2.69E-14 1.44E-15 0.00E+00 0.000 ng/dscm 3.55E-05 1.90E-06 0.00E+00 0.000 ng/dscm@7%O2 3.12E-05 1.66E-06 0.00E+00 0.000 

### Compound: Other PeCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0 0 0 0.000 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000 ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000 

### Compound: Other TCDD Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000558 0 0.00000000002 0.000 lb/mmBtuO2 3.75E-13 0.00E+00 1.40E-15 0.000 ng/dscm 4.95E-04 0.00E+00 1.92E-06 0.000 ng/dscm@7%O2 4.35E-04 0.00E+00 1.63E-06 0.000 

### Compound: Other TCDF Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000000164 0 0.00000000001 0.000 lb/mmBtuO2 1.10E-13 0.00E+00 7.02E-16 0.000 ng/dscm 1.45E-04 0.00E+00 9.60E-07 0.000 ng/dscm@7%O2 1.28E-04 0.00E+00 8.14E-07 0.000 

### Compound: Total Dioxins Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.000000202 0.000000047 0.000000139 0.000 lb/mmBtuO2 1.36E-11 3.37E-12 9.75E-12 0.000 ng/dscm 1.79E-02 4.48E-03 1.33E-02 0.012 ng/dscm@7%O2 1.57E-02 3.92E-03 1.13E-02 0.010 

### Compound: Total Furans Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.000000069 0.000000035 0.000000063 0.000 lb/mmBtuO2 4.64E-12 2.51E-12 4.42E-12 0.000 ng/dscm 6.12E-03 3.33E-03 6.05E-03 0.005 ng/dscm@7%O2 5.38E-03 2.91E-03 5.13E-03 0.004 

### Compound: Total TEQ Average RunNumber H8-M23-1 H8-M23-2 H8-M23-3 Mass_mg 0.00000001816 0.00000001592 0.0000000353 0.000 lb/mmBtuO2 1.22E-12 1.14E-12 2.48E-12 0.000



### Thursday, February 10, 2011 Page 15 of 31

### Emissions Testing Unit 8

ng/dscm 1.61E-03 1.52E-03 3.39E-03 0.002 ng/dscm@7%O2 1.42E-03 1.33E-03 2.87E-03 0.002



### Location: stack - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 1.00E-03 8.44E-04 2.15E-03 0.001 ppm 7.32E-01 6.19E-01 1.58E+00 0.977 ppm@7%O2 6.34E-01 5.34E-01 1.36E+00 0.843



### Location: stack - Method 26 Compound: Hydrogen Chloride Average RunNumber H8-M26-1 H8-M26-2 H8-M26-3 Mass_mg 1.263 1.077 0.828 1.056 lb/mmBtuO2 9.35E-04 7.60E-04 6.09E-04 0.001 

### Compound: Hydrogen Fluoride Average RunNumber H8-M26-1 H8-M26-2 H8-M26-3 Mass_mg 0.212 0.22 0.208 0.213 lb/mmBtuO2 1.57E-04 1.55E-04 1.53E-04 0.000



### Location: stack - Method 29 Compound: Antimony Average RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4 Mass_mg 0.002181 0.008204 0.005836 0.005 lb/mmBtuO2 3.03E-07 1.15E-06 8.12E-07 0.000 

### Compound: Arsenic Average RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4 Mass_mg 0.0178 0.02055 0.01782 0.019 lb/mmBtuO2 2.47E-06 2.89E-06 2.48E-06 0.000 

### Compound: Beryllium Average RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4 Mass_mg 0.00135 0.00215 0.00165 0.002 lb/mmBtuO2 1.88E-07 3.02E-07 2.30E-07 0.000 

### Compound: Cadmium Average RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4 Mass_mg 0.000371 0.00077 0.000722 0.001 lb/mmBtuO2 5.16E-08 1.08E-07 1.00E-07 0.000 

### Compound: Chromium Average RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4



### Thursday, February 10, 2011 Page 16 of 31

### Emissions Testing Unit 8

Mass_mg 0.009519 0.01799 0.01639 0.015 lb/mmBtuO2 1.32E-06 2.53E-06 2.28E-06 0.000 

### Compound: Cobalt Average RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4 Mass_mg 0.16095 0.2797 0.26182 0.234 lb/mmBtuO2 2.24E-05 3.93E-05 3.64E-05 0.000 

### Compound: Lead Average RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4 Mass_mg 0.004418 0.104 0.021812 0.043 lb/mmBtuO2 6.14E-07 1.46E-05 3.04E-06 0.000 

### Compound: Manganese Average RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4 Mass_mg 0.09386 0.08518 0.06652 0.082 lb/mmBtuO2 1.30E-05 1.20E-05 9.26E-06 0.000 

### Compound: Nickel Average RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4 Mass_mg 3.87007 6.79537 6.34017 5.669 lb/mmBtuO2 5.38E-04 9.55E-04 8.82E-04 0.001 

### Compound: Selenium Average RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4 Mass_mg 0.01192 0.00762 0.00662 0.009 lb/mmBtuO2 1.66E-06 1.07E-06 9.21E-07 0.000



### Location: stack - Method 5 Compound: Filterable Particulate Average RunNumber H8-M5/29-2 H8-M5/29-3 H8-M5/29-4 Mass_mg 89.7 251.3 145 162.000 lb/mmBtuO2 1.25E-02 3.53E-02 2.02E-02 0.023



### Location: stack - Method 6C Compound: Sulfur Dioxide Average Run 1 2 3 lb/mmBtuO2 3.69E-01 3.65E-01 3.64E-01 0.366 ppm 1.86E+02 1.84E+02 1.84E+02 184.667 ppm@7%O2 1.61E+02 1.59E+02 1.58E+02 159.333



### Location: stack - Method 7E Compound: Nitrogen oxides (NOx) Average Run 1 2 3



### Thursday, February 10, 2011 Page 17 of 31

### Emissions Testing Unit 8

Process Run Data lb/mmBtuO2 5.55E-01 5.54E-01 5.59E-01 0.556 ppm 3.89E+02 3.89E+02 3.94E+02 390.667 ppm@7%O2 3.37E+02 3.35E+02 3.39E+02 337.000



### Location: stack - OTM - 27/28 

### Compound: Filterable Particulate Average RunNumber H8-OTM27/28-2 H8-OTM27/28-3 H8-OTM27/28-4 Mass_mg 154.1 107.2 105.4 122.233 lb/mmBtuO2 3.22E-02 2.04E-02 2.18E-02 0.025 

### Compound: Filterable PM2.5 Average RunNumber H8-OTM27/28-2 H8-OTM27/28-3 H8-OTM27/28-4 Mass_mg 69 68.4 63.6 67.000 lb/mmBtuO2 1.44E-02 1.30E-02 1.31E-02 0.014 

### Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber H8-OTM27/28-2 H8-OTM27/28-3 H8-OTM27/28-4 Mass_mg 13.6 14.4 14.6 14.200 lb/mmBtuO2 2.84E-03 2.74E-03 3.02E-03 0.003 

### Compound: Organic Condensible Particulate Average RunNumber H8-OTM27/28-2 H8-OTM27/28-3 H8-OTM27/28-4 Mass_mg 1.3 0.4 1.9 1.200 lb/mmBtuO2 2.71E-04 7.62E-05 3.93E-04 0.000 

### Compound: Total Particulate Average RunNumber H8-OTM27/28-2 H8-OTM27/28-3 H8-OTM27/28-4 Mass_mg 167 120 119.9 135.633 lb/mmBtuO2 3.49E-02 2.29E-02 2.48E-02 0.028 

### Compound: Total PM2.5 Average RunNumber H8-OTM27/28-2 H8-OTM27/28-3 H8-OTM27/28-4 Mass_mg 81.9 81.2 78.1 80.400 lb/mmBtuO2 1.71E-02 1.55E-02 1.61E-02 0.016



### Thursday, February 10, 2011 Page 18 of 31

### Emissions Testing Unit 8

Process Run Data



### Run Name Value UOM Comments Target Value 1 0


### 2 0
1 0
2 0


### 1 0
2 0
1 0


### 2 0
1 0
2 0


### 1 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
2 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
1 0


### 1 Unit Gross Electric Generation 52.83 Mwe
1 Unit Net Electric Generation 49.84 MWh
1 Steam Output 430.63 1,000 lbs steam/hr EPA Method 30B Run H8-M30B-1 1 Average Heat Input 557.82 MMBtu/hr EPA Method 23 Run H8-M23-1 

### 1 Fuel Oil Firing Rate 29.39 Klb/hr April 16, 2010 Test Day 3 0
3 0


### 3 0
3 0
3 0


### 3 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
3 0
3 Unit Gross Electric Generation 51.53 Mwe


### 3 Unit Net Electric Generation 48.61 MWh
3 Steam Output 419.28 1,000 lbs steam/hr EPA Method 23 Run H8-M23-2 

### 3 Average Heat Input 543.47 MMBtu/hr EPA Method 5/29 Run H8-M5/29-2 3 Fuel Oil Firing Rate 28.53 Klb/hr April 17, 2010 Test Day



### Thursday, February 10, 2011 Page 19 of 31

### Emissions Testing Unit 8

4 0


### 4 0
4 0
4 0


### 4 0 EPA Method 18: Runs H8-M18-1, H8-M18-2, H8- M18-3 4 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
4 0 EPA Method 0031/SW-846 8260B Runs H8- M0031-1, H8- M0031-2, and H8- M0031-3 4 Unit Gross Electric Generation 51.92 Mwe EPA Method 0010/SW-846 8270D Runs H8- M0010-1, H8- M0010-2, and H8- M0010-2 

### 4 Unit Net Electric Generation 49.06 MWh EPA Method 316 Runs H8-M316-1, H8-M316-2, and H8-M316-3 4 Steam Output 420.87 1,000 lbs steam/hr EPA Method 26/CTM-033 Runs H8-M26-1, H8- M26-2, and H8- M26-3
4 Average Heat Input 547.62 MMBtu/hr EPA Method 3A, 6C, 7E, 10, and 25A Runs 1, 2, and 3
4 Fuel Oil Firing Rate 28.93 Klb/hr April 19, 2010 Test Day 

### 5 0
5 0
5 0


### 5 0
5 0
5 Residual Oil (No. 6) Burned 0 1000 Gallons/hr


### 5 0
5 Unit Gross Electric Generation 52.38 Mwe



### Thursday, February 10, 2011 Page 20 of 31

### Emissions Testing Unit 8

5 Unit Net Electric Generation 49.43 MWh EPA Method OTM 27/28 Run H8-OTM27/28-2 5 Steam Output 433.67 1,000 lbs steam/hr EPA Method 30B Run H8-M30B-2 

### 5 Average Heat Input 548.12 MMBtu/hr EPA Method 5/29 Run H8-M5/29-3 5 Fuel Oil Firing Rate 29.45 Klb/hr July 13, 2010 Test Day


### 6 0
6 0
6 0


### 6 0
6 0
6 Residual Oil (No. 6) Burned 0 1000 Gallons/hr


### 6 0
6 Unit Gross Electric Generation 52.76 Mwe EPA Method OTM 27/28 Run H8-OTM27/28-3


### 6 Unit Net Electric Generation 49.81 MWh EPA Method 30B Run H8-M30B-3
6 Steam Output 436.37 1,000 lbs steam/hr EPA Method 23 Run H8-M23-3
6 Average Heat Input 550.24 MMBtu/hr EPA Method 5/29 Run H8-M5/29-4
6 Fuel Oil Firing Rate 29.58 Klb/hr July 14, 2010 Test Day
7 0
7 0


### 7 0
7 0
7 0


### 7 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
7 0
7 Unit Gross Electric Generation 51.82 Mwe


### 7 Unit Net Electric Generation 48.86 MWh
7 Steam Output 428.59 1,000 lbs steam/hr
7 Average Heat Input 543.47 MMBtu/hr EPA Method OTM 27/28 Run H8-OTM27/28-4
7 Fuel Oil Firing Rate 28.99 Klb/hr July 15, 2010 Test Day



### Thursday, February 10, 2011 Page 21 of 31

### Emissions Testing Unit 8

APCD Run Data

Process Lab Run Data 

### Run Name Value UOM Comments Target Value 1 None 0


### 1 0
1 0
1 0

Run Name Value UOM Comments 

### 1 none 0 1 0 1 0 

### 1 0 1 0



### Thursday, February 10, 2011 Page 22 of 31

### Emissions Testing Unit 8

Sampling / Stack Data Results Detail



### Location stack - Method 10 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 23 of 31

### Emissions Testing Unit 8

Location stack - Method 23 Average Run Number H8-M23-1 H8-M23-2 H8-M23-3 Test Date 4/16/2010 4/17/2010 7/14/2010 Run Start Time 7:25:00 AM 7:30:00 AM 7:35:00 AM Run Finish Time 3:48:00 PM 3:54:00 PM 4:16:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 480 480 480 Nozzle Diameter, inches 0.259 0.259 0.26 0.259 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 1.02 1.02 1.03 1.023 Barometric Pressure, inches of Mercury 30.1 30.1 30 30.067 Average Orifice Meter Differential, inches H2O 2.53 2.27 2.40 2.400 Dry Gas Meter Volume Sampled, cubic feet 397.303 371.023 373.490 380.605 Average Dry Gas Meter Temperature, °F 83.73 85.02 96.77 88.507 Dry Gas Meter Volume Sampled, dscf 398.340 370.876 367.944 379.053 Total Moisture Liquid collected, g 1024.3 967.6 951.4 981.100 Volume of Water Vapor, standard cubic feet 48.21 45.54 44.78 46.177 Moisture Content of Stack Gas, % 10.80 10.94 10.85 10.863 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.892 0.8906 0.8915 0.891 Carbon Dioxide, % 12 12 12.5 12.167 Oxygen, % 5.1 5 4.5 4.867 Carbon Monoxide & Nitrogen, % 82.9 83 83 82.967 Fuel Factor 1.32 1.33 1.31 Dry Molecular Weight, lb/lb-Mole 30.12 30.12 30.18 30.140 Wet Molecular weight, lb/lb-Mole 28.81 28.79 28.86 28.820 Flue Gas Static Pressure, inches of H2O -0.81 -0.68 -0.55 -0.680 Absolute Flue Gas Pressure, inches of Mercury 30.04 30.05 29.96 30.017 Average Stack Gas Temperature, °F 310.71 305.88 317.25 311.280 Average Velocity Head, inches of H2O 0.8068813315 574 0.719943260

182994 0.706937852

158604 0.745
Average Stack Gas Velocity, feet/second 60.87 57.33 57.25 58.483 Stack Cross-Sectional Area, square feet 63.617 63.617 63.617 63.617 Dry Volumetric Flow Rate, dry scfm 142,552.2 134,941.4 132,517.9 136,670.500 Actual Wet Volumetric Flue Gas Flow Rate, acfm 232,342.0 218,829.8 218,524.4 223,232.067 Percent Isokinetic of Sampling Rate, % 101.2 99.6 99.8 100.200 Percent Excess Air, % 30.4 29.6 25.8 28.600 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Round Duct Diameter, inches 108 108 108 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Thursday, February 10, 2011 Page 24 of 31

### Emissions Testing Unit 8

Location stack - Method 25A Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 25 of 31

### Emissions Testing Unit 8

Location stack - Method 26 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 10, 2011 Page 26 of 31

### Emissions Testing Unit 8

Location stack - Method 29 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 10, 2011 Page 27 of 31

### Emissions Testing Unit 8

Location stack - Method 5 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 10, 2011 Page 28 of 31

### Emissions Testing Unit 8

Location stack - Method 6C Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 29 of 31

### Emissions Testing Unit 8

Location stack - Method 7E Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 30 of 31

### Emissions Testing Unit 8

Location stack - OTM - 27/28 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 10, 2011 Page 31 of 31