Name:

Title:

Company:

Sign Date:

Name: Thomas F. Mattei

Title: Quality Assurance Manager / Techni

Company: Avogadro Environmental Corporatio

Sign Date: 6/29/2010

Permitted Facility Representative / Date Testing Company Representative / Date

PPL Generation, LLC - Brunner Island Station Units 1/2

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Tuesday, February 01, 2011 Page 1 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Facility Information:

PPL Brunner Island, LLC

Wago Road

York Haven PA 17370

Contact: Deborah Runkle

Phone: 717-266-7550

Fax:

Email:

Testing Company:

Avogadro Environmental Corporation

1350 Sullivan Trail, Suite A

Easton PA 18040

Contact:Thomas Mattei

Phone: 610-559-8776 x 103

Fax: 610-559-8913

Email: tmattei@avogadro.net

Air Permit Number:

67-05005

Permitted Source ID/Name:

031A/032 Unit 1 / 2

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

The PPL Brunner Island, LLC facility is located in York Haven, York County, Pennsylvania. Units 1 and 2 are 

Combustion Engineering pulverized coal-fired boilers used to supply steam to a General Electric 350 megawatt 

(MW) and 400 MW turbine. Exhaust gases from Unit 1 pass through a baghouse and Unit 2 exhaust gases pass 

through an Electrostatic Precipitator (ESP). Exhaust from the Unit 1 baghouse and Unit 2 ESP flow into the Flue Gas 

Desulfurization (FGD) system where they combine and are then discharged through a common fiberglass flue inside a 

single concrete shell.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 4213300024 FRS #: 110000601778

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 368 0 0 0 816 4176 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

% H2O Method 1 - 4 3 60 0 Runs range from 60 to 

240 minutes

Stack Exit

Tuesday, February 01, 2011 Page 2 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Hydrogen Fluoride Method 26A 3 60 0 The samples were 

collected in a 

combined train with 

HCN using NaOH

impingers only.

Method 26A & CTM033

The MDLs are 

determined by the 

analysis of at least 

seven replicate 

standards at a 

concentration near the 

expected MDL. To 

determine the MDL 

value, the standard 

deviation of the 

replicate analyses is 

calculated and that 

number is multiplied 

by the Student t factor 

that corresponds to the 

number of replicates 

analyzed. The MDL 

value should meet the 

criteria stated in the 

CFR Title 40, Part 136 

B.

If the MDL 

determined does not 

meet these criteria, a 

default MDL value 

will be used which is 

1/10 of the 

concentration of the 

standard used to 

produce the MDL 

value.

Stack Exit

Tuesday, February 01, 2011 Page 3 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Hydrogen Chloride Method 26A 3 60 0 The samples were 

collected in a 

combined train with 

HCN using NaOH

impingers only. 

Chlorine data for 

Method 26A analysis 

is not available from 

the laboratory.

Method 26A & CTM033

The MDLs are 

determined by the 

analysis of at least 

seven replicate 

standards at a 

concentration near the 

expected MDL. To 

determine the MDL 

value, the standard 

deviation of the 

replicate analyses is 

calculated and that 

number is multiplied 

by the Student t factor 

that corresponds to the 

number of replicates 

analyzed. The MDL 

value should meet the 

criteria stated in the 

CFR Title 40, Part 136 

B.

If the MDL 

determined does not 

meet these criteria, a 

default MDL value 

will be used which is 

1/10 of the 

concentration of the 

standard used to 

produce the MDL 

value.

Stack Exit

Tuesday, February 01, 2011 Page 4 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Cadmium Method 29 3 240 0 Method 29 

For Method 29 the 

analyst takes the 

statistically 

determined MDL 

(Method Detection 

Limit) value and 

multiplies it by a 

“factor” in order to 

determine the RDL 

(Reporting Detection 

Limit). This process is 

similar to the one 

employed in Method 

23 where the EDL is 

determined based on a 

constant factor of 2.5 

times the signal to 

noise ratio. 

For the ICP/MS this 

“factor” can vary. The 

factor is determined 

by the analyst at the 

bench and takes into 

account all relevant 

factors such as, final 

volumes, 

interferences, matrix 

issues, etc. The RDL 

(Reporting Detection 

Limit) reported is the 

lowest concentration 

that the lab feels can 

be reported within the 

99% confidence 

interval. For values 

below this RDL the 

uncertainty increases. 

Section 5.5.5.2.2.1 

bullet H refers to the 

ICP/MS procedure.

Stack Exit

Tuesday, February 01, 2011 Page 5 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Mercury Method 29 3 240 0 Method 29 

For Method 29 the 

analyst takes the 

statistically 

determined MDL 

(Method Detection 

Limit) value and 

multiplies it by a 

“factor” in order to 

determine the RDL 

(Reporting Detection 

Limit). This process is 

similar to the one 

employed in Method 

23 where the EDL is 

determined based on a 

constant factor of 2.5 

times the signal to 

noise ratio. 

For the ICP/MS this 

“factor” can vary. The 

factor is determined 

by the analyst at the 

bench and takes into 

account all relevant 

factors such as, final 

volumes, 

interferences, matrix 

issues, etc. The RDL 

(Reporting Detection 

Limit) reported is the 

lowest concentration 

that the lab feels can 

be reported within the 

99% confidence 

interval. For values 

below this RDL the 

uncertainty increases. 

Section 5.5.5.2.2.1 

bullet H refers to the 

ICP/MS procedure.

Stack Exit

Tuesday, February 01, 2011 Page 6 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Nickel Method 29 3 240 0 Method 29 

For Method 29 the 

analyst takes the 

statistically 

determined MDL 

(Method Detection 

Limit) value and 

multiplies it by a 

“factor” in order to 

determine the RDL 

(Reporting Detection 

Limit). This process is 

similar to the one 

employed in Method 

23 where the EDL is 

determined based on a 

constant factor of 2.5 

times the signal to 

noise ratio. 

For the ICP/MS this 

“factor” can vary. The 

factor is determined 

by the analyst at the 

bench and takes into 

account all relevant 

factors such as, final 

volumes, 

interferences, matrix 

issues, etc. The RDL 

(Reporting Detection 

Limit) reported is the 

lowest concentration 

that the lab feels can 

be reported within the 

99% confidence 

interval. For values 

below this RDL the 

uncertainty increases. 

Section 5.5.5.2.2.1 

bullet H refers to the 

ICP/MS procedure.

Stack Exit

Tuesday, February 01, 2011 Page 7 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Selenium Method 29 3 240 0 Method 29 

For Method 29 the 

analyst takes the 

statistically 

determined MDL 

(Method Detection 

Limit) value and 

multiplies it by a 

“factor” in order to 

determine the RDL 

(Reporting Detection 

Limit). This process is 

similar to the one 

employed in Method 

23 where the EDL is 

determined based on a 

constant factor of 2.5 

times the signal to 

noise ratio. 

For the ICP/MS this 

“factor” can vary. The 

factor is determined 

by the analyst at the 

bench and takes into 

account all relevant 

factors such as, final 

volumes, 

interferences, matrix 

issues, etc. The RDL 

(Reporting Detection 

Limit) reported is the 

lowest concentration 

that the lab feels can 

be reported within the 

99% confidence 

interval. For values 

below this RDL the 

uncertainty increases. 

Section 5.5.5.2.2.1 

bullet H refers to the 

ICP/MS procedure.

Stack Exit

Tuesday, February 01, 2011 Page 8 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Antimony Method 29 3 240 0 Method 29 

For Method 29 the 

analyst takes the 

statistically 

determined MDL 

(Method Detection 

Limit) value and 

multiplies it by a 

“factor” in order to 

determine the RDL 

(Reporting Detection 

Limit). This process is 

similar to the one 

employed in Method 

23 where the EDL is 

determined based on a 

constant factor of 2.5 

times the signal to 

noise ratio. 

For the ICP/MS this 

“factor” can vary. The 

factor is determined 

by the analyst at the 

bench and takes into 

account all relevant 

factors such as, final 

volumes, 

interferences, matrix 

issues, etc. The RDL 

(Reporting Detection 

Limit) reported is the 

lowest concentration 

that the lab feels can 

be reported within the 

99% confidence 

interval. For values 

below this RDL the 

uncertainty increases. 

Section 5.5.5.2.2.1 

bullet H refers to the 

ICP/MS procedure.

Stack Exit

Tuesday, February 01, 2011 Page 9 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Lead Method 29 3 240 0 Method 29 

For Method 29 the 

analyst takes the 

statistically 

determined MDL 

(Method Detection 

Limit) value and 

multiplies it by a 

“factor” in order to 

determine the RDL 

(Reporting Detection 

Limit). This process is 

similar to the one 

employed in Method 

23 where the EDL is 

determined based on a 

constant factor of 2.5 

times the signal to 

noise ratio. 

For the ICP/MS this 

“factor” can vary. The 

factor is determined 

by the analyst at the 

bench and takes into 

account all relevant 

factors such as, final 

volumes, 

interferences, matrix 

issues, etc. The RDL 

(Reporting Detection 

Limit) reported is the 

lowest concentration 

that the lab feels can 

be reported within the 

99% confidence 

interval. For values 

below this RDL the 

uncertainty increases. 

Section 5.5.5.2.2.1 

bullet H refers to the 

ICP/MS procedure.

Stack Exit

Tuesday, February 01, 2011 Page 10 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Cobalt Method 29 3 240 0 Method 29 

For Method 29 the 

analyst takes the 

statistically 

determined MDL 

(Method Detection 

Limit) value and 

multiplies it by a 

“factor” in order to 

determine the RDL 

(Reporting Detection 

Limit). This process is 

similar to the one 

employed in Method 

23 where the EDL is 

determined based on a 

constant factor of 2.5 

times the signal to 

noise ratio. 

For the ICP/MS this 

“factor” can vary. The 

factor is determined 

by the analyst at the 

bench and takes into 

account all relevant 

factors such as, final 

volumes, 

interferences, matrix 

issues, etc. The RDL 

(Reporting Detection 

Limit) reported is the 

lowest concentration 

that the lab feels can 

be reported within the 

99% confidence 

interval. For values 

below this RDL the 

uncertainty increases. 

Section 5.5.5.2.2.1 

bullet H refers to the 

ICP/MS procedure.

Stack Exit

Tuesday, February 01, 2011 Page 11 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Manganese Method 29 3 240 0 Method 29 

For Method 29 the 

analyst takes the 

statistically 

determined MDL 

(Method Detection 

Limit) value and 

multiplies it by a 

“factor” in order to 

determine the RDL 

(Reporting Detection 

Limit). This process is 

similar to the one 

employed in Method 

23 where the EDL is 

determined based on a 

constant factor of 2.5 

times the signal to 

noise ratio. 

For the ICP/MS this 

“factor” can vary. The 

factor is determined 

by the analyst at the 

bench and takes into 

account all relevant 

factors such as, final 

volumes, 

interferences, matrix 

issues, etc. The RDL 

(Reporting Detection 

Limit) reported is the 

lowest concentration 

that the lab feels can 

be reported within the 

99% confidence 

interval. For values 

below this RDL the 

uncertainty increases. 

Section 5.5.5.2.2.1 

bullet H refers to the 

ICP/MS procedure.

Stack Exit

Tuesday, February 01, 2011 Page 12 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Chromium Method 29 3 240 0 Method 29 

For Method 29 the 

analyst takes the 

statistically 

determined MDL 

(Method Detection 

Limit) value and 

multiplies it by a 

“factor” in order to 

determine the RDL 

(Reporting Detection 

Limit). This process is 

similar to the one 

employed in Method 

23 where the EDL is 

determined based on a 

constant factor of 2.5 

times the signal to 

noise ratio. 

For the ICP/MS this 

“factor” can vary. The 

factor is determined 

by the analyst at the 

bench and takes into 

account all relevant 

factors such as, final 

volumes, 

interferences, matrix 

issues, etc. The RDL 

(Reporting Detection 

Limit) reported is the 

lowest concentration 

that the lab feels can 

be reported within the 

99% confidence 

interval. For values 

below this RDL the 

uncertainty increases. 

Section 5.5.5.2.2.1 

bullet H refers to the 

ICP/MS procedure.

Stack Exit

Tuesday, February 01, 2011 Page 13 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Filterable Particulate Method 29 3 240 0 Method 29 

For Method 29 the 

analyst takes the 

statistically 

determined MDL 

(Method Detection 

Limit) value and 

multiplies it by a 

“factor” in order to 

determine the RDL 

(Reporting Detection 

Limit). This process is 

similar to the one 

employed in Method 

23 where the EDL is 

determined based on a 

constant factor of 2.5 

times the signal to 

noise ratio. 

For the ICP/MS this 

“factor” can vary. The 

factor is determined 

by the analyst at the 

bench and takes into 

account all relevant 

factors such as, final 

volumes, 

interferences, matrix 

issues, etc. The RDL 

(Reporting Detection 

Limit) reported is the 

lowest concentration 

that the lab feels can 

be reported within the 

99% confidence 

interval. For values 

below this RDL the 

uncertainty increases. 

Section 5.5.5.2.2.1 

bullet H refers to the 

ICP/MS procedure.

Stack Exit

Tuesday, February 01, 2011 Page 14 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Beryllium Method 29 3 240 0 Method 29 

For Method 29 the 

analyst takes the 

statistically 

determined MDL 

(Method Detection 

Limit) value and 

multiplies it by a 

“factor” in order to 

determine the RDL 

(Reporting Detection 

Limit). This process is 

similar to the one 

employed in Method 

23 where the EDL is 

determined based on a 

constant factor of 2.5 

times the signal to 

noise ratio. 

For the ICP/MS this 

“factor” can vary. The 

factor is determined 

by the analyst at the 

bench and takes into 

account all relevant 

factors such as, final 

volumes, 

interferences, matrix 

issues, etc. The RDL 

(Reporting Detection 

Limit) reported is the 

lowest concentration 

that the lab feels can 

be reported within the 

99% confidence 

interval. For values 

below this RDL the 

uncertainty increases. 

Section 5.5.5.2.2.1 

bullet H refers to the 

ICP/MS procedure.

Stack Exit

Tuesday, February 01, 2011 Page 15 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Arsenic Method 29 3 240 0 Method 29 

For Method 29 the 

analyst takes the 

statistically 

determined MDL 

(Method Detection 

Limit) value and 

multiplies it by a 

“factor” in order to 

determine the RDL 

(Reporting Detection 

Limit). This process is 

similar to the one 

employed in Method 

23 where the EDL is 

determined based on a 

constant factor of 2.5 

times the signal to 

noise ratio. 

For the ICP/MS this 

“factor” can vary. The 

factor is determined 

by the analyst at the 

bench and takes into 

account all relevant 

factors such as, final 

volumes, 

interferences, matrix 

issues, etc. The RDL 

(Reporting Detection 

Limit) reported is the 

lowest concentration 

that the lab feels can 

be reported within the 

99% confidence 

interval. For values 

below this RDL the 

uncertainty increases. 

Section 5.5.5.2.2.1 

bullet H refers to the 

ICP/MS procedure.

Stack Exit

Co2 Method 3A CO2 3 240 0 Runs range from 62 to 

278 minutes

Stack Exit

O2 Method 3A O2 3 62 0 Runs range from 62 to 

278 minutes

Stack Exit

Tuesday, February 01, 2011 Page 16 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Inorganic (Aqueous) 

Condensible Part.

Method 5/OTM-28 3 240 0 Back half particulate 

matter (OTM-028) 

mass was calculated 

using the maximum 

allowable blank 

correction value of 

0.002 g. A correction 

value for each fraction 

was calculated by 

dividing the fraction 

blank amount by the 

total back half blank 

amount and 

multiplying that by the 

allowable blank 

correction value of 

0.002 g. 

Method OTM-028

A portion of reagent 

water that has been 

spiked with a known 

amount of material is 

extracted 3 times with 

Methylene Chloride. 

The solvent is 

evaporated to dryness. 

Detection Limits are 

calculated by using the 

standard deviation 

from these 10 replicate 

low level spikes. The 

standard deviation is 

multiplied by the 

appropriate Student T 

value to determine the 

statistically derived 

reporting limit. The 

non-extractable 

portion is determined 

by the weight 

difference on a series 

of 10 vials. Detection 

Limits are calculated 

by using the standard 

deviation from these 

10 replicates. The 

standard deviation is 

multiplied by the 

appropriate Student T 

value to determine the 

statistically derived 

reporting limit.

Stack Exit

Tuesday, February 01, 2011 Page 17 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Organic Condensible 

Particulate

Method 5/OTM-28 3 240 0 Back half particulate 

matter (OTM-028) 

mass was calculated 

using the maximum 

allowable blank 

correction value of 

0.002 g. A correction 

value for each fraction 

was calculated by 

dividing the fraction 

blank amount by the 

total back half blank 

amount and 

multiplying that by the 

allowable blank 

correction value of 

0.002 g. 

Method OTM-028

A portion of reagent 

water that has been 

spiked with a known 

amount of material is 

extracted 3 times with 

Methylene Chloride. 

The solvent is 

evaporated to dryness. 

Detection Limits are 

calculated by using the 

standard deviation 

from these 10 replicate 

low level spikes. The 

standard deviation is 

multiplied by the 

appropriate Student T 

value to determine the 

statistically derived 

reporting limit. The 

non-extractable 

portion is determined 

by the weight 

difference on a series 

of 10 vials. Detection 

Limits are calculated 

by using the standard 

deviation from these 

10 replicates. The 

standard deviation is 

multiplied by the 

appropriate Student T 

value to determine the 

statistically derived 

reporting limit.

Stack Exit

Tuesday, February 01, 2011 Page 18 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Total Particulate Method 5/OTM-28 3 240 0 Method OTM-028

A portion of reagent 

water that has been 

spiked with a known 

amount of material is 

extracted 3 times with 

Methylene Chloride. 

The solvent is 

evaporated to dryness. 

Detection Limits are 

calculated by using the 

standard deviation 

from these 10 replicate 

low level spikes. The 

standard deviation is 

multiplied by the 

appropriate Student T 

value to determine the 

statistically derived 

reporting limit. The 

non-extractable 

portion is determined 

by the weight 

difference on a series 

of 10 vials. Detection 

Limits are calculated 

by using the standard 

deviation from these 

10 replicates. The 

standard deviation is 

multiplied by the 

appropriate Student T 

value to determine the 

statistically derived 

reporting limit.

Stack Exit

Tuesday, February 01, 2011 Page 19 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Filterable Particulate Method 5/OTM-28 3 240 0 Pursuant to Method 5, 

no blank filter was 

analyzed or blank 

filter correction 

performed.

Method OTM-028

A portion of reagent 

water that has been 

spiked with a known 

amount of material is 

extracted 3 times with 

Methylene Chloride. 

The solvent is 

evaporated to dryness. 

Detection Limits are 

calculated by using the 

standard deviation 

from these 10 replicate 

low level spikes. The 

standard deviation is 

multiplied by the 

appropriate Student T 

value to determine the 

statistically derived 

reporting limit. The 

non-extractable 

portion is determined 

by the weight 

difference on a series 

of 10 vials. Detection 

Limits are calculated 

by using the standard 

deviation from these 

10 replicates. The 

standard deviation is 

multiplied by the 

appropriate Student T 

value to determine the 

statistically derived 

reporting limit.

Stack Exit

Sulfur Dioxide Method 6C 3 62 0 Runs range from 62 to 

78 minutes

Stack Exit

Nitrogen oxides (NOx) Method 7E 3 62 0 Runs range from 62 to 

78 minutes

Stack Exit

Tuesday, February 01, 2011 Page 20 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Sampling / Stack Data Results Summary

Location Stack Exit - Method 26A

Average

Run Number M26A-2 M26A-3 M26A-4

Test Date 4/21/2010 4/21/2010 4/21/2010

Run Start Time 3:10:00 PM 5:00:00 PM 6:40:00 PM

Run Finish Time 4:32:00 PM 6:20:00 PM 7:58:00 PM

Net Run Time, minutes 60 60 60

Dry Gas Meter Volume Sampled, dscf 33.249 33.485 33.789 33.508

Moisture Content of Stack Gas, % 21.15 19.32 20.19 20.220

Moisture Saturation at Stack Gas Temperature, % 14.07 14.13 14.28 14.160

Carbon Dioxide, % 13.34 13.43 12.99 13.253

Oxygen, % 5.73 5.69 5.45 5.623

Average Stack Gas Temperature, °F 127.15 127.31 127.69 127.383

Dry Volumetric Flow Rate, dry scfm 1,476,789.3 1,505,126.0 1,520,862.6 1,500,925.96

7

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,922,044.8 1,961,487.2 1,986,748.1 1,956,760.03

3

Percent Isokinetic of Sampling Rate, % 106.0 104.7 104.6 105.100

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Tuesday, February 01, 2011 Page 21 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack Exit - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Tuesday, February 01, 2011 Page 22 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Tuesday, February 01, 2011 Page 23 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Emissions Summary

Location: Stack Exit - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber M26A-2 M26A-3 M26A-4

Mass_mg 0.459 0.465 0.432 0.452

lb/mmBtuO2 4.10E-04 4.11E-04 3.73E-04 0.000

Compound: Hydrogen Fluoride

Average

RunNumber M26A-2 M26A-3 M26A-4

Mass_mg 0.47 0.476 0.442 0.463

lb/mmBtuO2 4.20E-04 4.21E-04 3.82E-04 0.000

Location: Stack Exit - Method 29

Compound: Antimony

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0028 0.0028 0.0028 0.003

lb/mmBtuO2 6.12E-07 6.07E-07 5.92E-07 0.000

Compound: Arsenic

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.004 0.00377 0.00381 0.004

lb/mmBtuO2 8.74E-07 8.17E-07 8.06E-07 0.000

Compound: Beryllium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0007 0.0007 0.0007 0.001

lb/mmBtuO2 1.53E-07 1.52E-07 1.48E-07 0.000

Compound: Cadmium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00072 0.0007 0.0007 0.001

lb/mmBtuO2 1.57E-07 1.52E-07 1.48E-07 0.000

Compound: Chromium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00905 0.02234 0.03344 0.022

lb/mmBtuO2 1.98E-06 4.84E-06 7.07E-06 0.000

Compound: Cobalt

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00198 0.00217 0.00154 0.002

lb/mmBtuO2 4.33E-07 4.70E-07 3.26E-07 0.000

Tuesday, February 01, 2011 Page 24 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Compound: Filterable Particulate

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 122.8 108.6 115.5 115.633

lb/mmBtuO2 2.68E-02 2.35E-02 2.44E-02 0.025

Compound: Lead

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00291 0.00166 0.00319 0.003

lb/mmBtuO2 6.36E-07 3.60E-07 6.75E-07 0.000

Compound: Manganese

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.02133 0.01113 0.01443 0.016

lb/mmBtuO2 4.66E-06 2.41E-06 3.05E-06 0.000

Compound: Mercury

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00556 0.00515 0.00567 0.005

lb/mmBtuO2 1.21E-06 1.12E-06 1.20E-06 0.000

Compound: Nickel

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.01796 0.07656 0.11136 0.069

lb/mmBtuO2 3.92E-06 1.66E-05 2.36E-05 0.000

Compound: Selenium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.1084 0.1174 0.0977 0.108

lb/mmBtuO2 2.37E-05 2.55E-05 2.07E-05 0.000

Location: Stack Exit - Method 5/OTM-28

Compound: Filterable Particulate

Average

RunNumber OTM28-1 OTM28-2 OTM28-3

Mass_mg 107 144.9 111.3 121.067

lb/mmBtuO2 2.33E-02 3.12E-02 2.37E-02 0.026

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber OTM28-1 OTM28-2 OTM28-3

Mass_mg 15.5 19.5 29.5 21.500

lb/mmBtuO2 3.38E-03 4.20E-03 6.29E-03 0.005

Compound: Organic Condensible Particulate

Average

RunNumber OTM28-1 OTM28-2 OTM28-3

Mass_mg 3.4 4.2 5.4 4.333

Tuesday, February 01, 2011 Page 25 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Process Run Data

lb/mmBtuO2 7.42E-04 9.06E-04 1.15E-03 0.001

Compound: Total Particulate

Average

RunNumber OTM28-1 OTM28-2 OTM28-3

Mass_mg 125.9 168.6 146.2 146.900

lb/mmBtuO2 2.75E-02 3.64E-02 3.12E-02 0.032

Location: Stack Exit - Method 6C

Compound: Sulfur Dioxide

Average

Run 2 3 4

lb/mmBtuO2 4.24E-01 4.14E-01 3.70E-01 0.403

ppm 1.89E+02 1.85E+02 1.68E+02 180.667

ppm@7%O2 1.73E+02 1.69E+02 1.51E+02 164.333

Location: Stack Exit - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 2 3 4

lb/mmBtuO2 3.20E-01 3.22E-01 3.09E-01 0.317

ppm 1.99E+02 2.00E+02 1.96E+02 198.333

ppm@7%O2 1.82E+02 1.83E+02 1.76E+02 180.333

Tuesday, February 01, 2011 Page 26 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Coal Burned 0 1000 Tons/hr

10 Coal Burned 0 1000 Tons/hr

11 Coal Burned 0 1000 Tons/hr

12 Coal Burned 0 1000 Tons/hr

2 Coal Burned 0 1000 Tons/hr

3 Coal Burned 0 1000 Tons/hr

4 Coal Burned 0 1000 Tons/hr

5 Coal Burned 0 1000 Tons/hr

6 Coal Burned 0 1000 Tons/hr

7 Coal Burned 0 1000 Tons/hr

8 Coal Burned 0 1000 Tons/hr

9 Coal Burned 0 1000 Tons/hr

1 Average Heat Input 6240 MMBtu/hr

10 Average Heat Input 6198 MMBtu/hr

11 Average Heat Input 6206 MMBtu/hr

12 Average Heat Input 6191 MMBtu/hr

2 Average Heat Input 6251 MMBtu/hr

3 Average Heat Input 6209 MMBtu/hr

4 Average Heat Input 6198 MMBtu/hr

5 Average Heat Input 6206 MMBtu/hr

6 Average Heat Input 6191 MMBtu/hr

7 Average Heat Input 6240 MMBtu/hr

8 Average Heat Input 6251 MMBtu/hr

9 Average Heat Input 6209 MMBtu/hr

1 Steam Output 2166 1000 lb steam/hr

10 Steam Output 2539 1000 lb steam/hr

11 Steam Output 2546 1000 lb steam/hr

12 Steam Output 2551 1000 lb steam/hr

2 Steam Output 2162 1000 lb steam/hr

3 Steam Output 2132 1000 lb steam/hr

4 Steam Output 2108 1000 lb steam/hr

5 Steam Output 2100 1000 lb steam/hr

6 Steam Output 2094 1000 lb steam/hr

Tuesday, February 01, 2011 Page 27 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

7 Steam Output 2469 1000 lb steam/hr

8 Steam Output 2491 1000 lb steam/hr

9 Steam Output 2565 1000 lb steam/hr

1 Fuel Oil Firing Rate 20 gal/hr

10 Fuel Oil Firing Rate 10 gal/hr

11 Fuel Oil Firing Rate 31 gal/hr

12 Fuel Oil Firing Rate 46 gal/hr

2 Fuel Oil Firing Rate 0 gal/hr

3 Fuel Oil Firing Rate 8 gal/hr

4 Fuel Oil Firing Rate 23 gal/hr

5 Fuel Oil Firing Rate 18 gal/hr

6 Fuel Oil Firing Rate 22 gal/hr

7 Fuel Oil Firing Rate 0 gal/hr

8 Fuel Oil Firing Rate 0 gal/hr

9 Fuel Oil Firing Rate 0 gal/hr

1 Flue Gas Flow Rate 97407 wKscfh

10 Flue Gas Flow Rate 97227 wKscfh

11 Flue Gas Flow Rate 97037 wKscfh

12 Flue Gas Flow Rate 96670 wKscfh

4 Flue Gas Flow Rate 97227 wKscfh

5 Flue Gas Flow Rate 97037 wKscfh

6 Flue Gas Flow Rate 96670 wKscfh

7 Flue Gas Flow Rate 97407 wKscfh

8 Flue Gas Flow Rate 97245 wKscfh

9 Flue Gas Flow Rate 96732 wKscfh

1 Pressure Drop Across FGD (if applicable) 4.2 in H20

10 Pressure Drop Across FGD (if applicable) 4.3 in H20

11 Pressure Drop Across FGD (if applicable) 4.3 in H20

12 Pressure Drop Across FGD (if applicable) 4.2 in H20

4 Pressure Drop Across FGD (if applicable) 4.3 in H20

5 Pressure Drop Across FGD (if applicable) 4.3 in H20

6 Pressure Drop Across FGD (if applicable) 4.2 in H20

7 Pressure Drop Across FGD (if applicable) 4.2 in H20

8 Pressure Drop Across FGD (if applicable) 4.2 in H20

9 Pressure Drop Across FGD (if applicable) 4.3 in H20

1 FGD Scrubber Liquor pH 5.6 pH

Tuesday, February 01, 2011 Page 28 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

10 FGD Scrubber Liquor pH 5.4 pH

11 FGD Scrubber Liquor pH 5.4 pH

12 FGD Scrubber Liquor pH 5.5 pH

4 FGD Scrubber Liquor pH 5.4 pH

5 FGD Scrubber Liquor pH 5.4 pH

6 FGD Scrubber Liquor pH 5.5 pH

7 FGD Scrubber Liquor pH 5.6 pH

8 FGD Scrubber Liquor pH 5.5 pH

9 FGD Scrubber Liquor pH 5.6 pH

1 FGD Scrubber Liquor Flow Rate 198 gal/min

10 FGD Scrubber Liquor Flow Rate 217 gal/min

11 FGD Scrubber Liquor Flow Rate 191 gal/min

12 FGD Scrubber Liquor Flow Rate 205 gal/min

4 FGD Scrubber Liquor Flow Rate 217 gal/min

5 FGD Scrubber Liquor Flow Rate 191 gal/min

6 FGD Scrubber Liquor Flow Rate 205 gal/min

7 FGD Scrubber Liquor Flow Rate 198 gal/min

8 FGD Scrubber Liquor Flow Rate 197 gal/min

9 FGD Scrubber Liquor Flow Rate 201 gal/min

1 Flue Gas Oxygen Content 3.5 %

10 Flue Gas Oxygen Content 3.7 %

11 Flue Gas Oxygen Content 3.7 %

12 Flue Gas Oxygen Content 3.7 %

4 Flue Gas Oxygen Content 3.5 %

5 Flue Gas Oxygen Content 3.5 %

6 Flue Gas Oxygen Content 3.5 %

7 Flue Gas Oxygen Content 3.7 %

8 Flue Gas Oxygen Content 3.7 %

9 Flue Gas Oxygen Content 3.7 %

1 Flue Gas Carbon Dioxide Content 11.5 %

10 Flue Gas Carbon Dioxide Content 11.5 %

11 Flue Gas Carbon Dioxide Content 11.5 %

12 Flue Gas Carbon Dioxide Content 11.5 %

4 Flue Gas Carbon Dioxide Content 11.5 %

5 Flue Gas Carbon Dioxide Content 11.5 %

6 Flue Gas Carbon Dioxide Content 11.5 %

Tuesday, February 01, 2011 Page 29 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

7 Flue Gas Carbon Dioxide Content 11.5 %

8 Flue Gas Carbon Dioxide Content 11.6 %

9 Flue Gas Carbon Dioxide Content 11.5 %

1 Flue Gas Moisture Content 0 %

10 Flue Gas Moisture Content 0 %

11 Flue Gas Moisture Content 0 %

12 Flue Gas Moisture Content 0 %

4 Flue Gas Moisture Content 0 %

5 Flue Gas Moisture Content 0 %

6 Flue Gas Moisture Content 0 %

7 Flue Gas Moisture Content 0 %

8 Flue Gas Moisture Content 0 %

9 Flue Gas Moisture Content 0 %

1 Flue Gas Sampling Point Temperature 125 Deg F

10 Flue Gas Sampling Point Temperature 126 Deg F

11 Flue Gas Sampling Point Temperature 126 Deg F

12 Flue Gas Sampling Point Temperature 126 Deg F

4 Flue Gas Sampling Point Temperature 126 Deg F

5 Flue Gas Sampling Point Temperature 126 Deg F

6 Flue Gas Sampling Point Temperature 126 Deg F

7 Flue Gas Sampling Point Temperature 125 Deg F

8 Flue Gas Sampling Point Temperature 125 Deg F

9 Flue Gas Sampling Point Temperature 125 Deg F

1 Flue Gas Pressure 0.97 atm

10 Flue Gas Pressure 0.96 atm

11 Flue Gas Pressure 0.96 atm

12 Flue Gas Pressure 0.96 atm

4 Flue Gas Pressure 0.96 atm

5 Flue Gas Pressure 0.96 atm

6 Flue Gas Pressure 0.96 atm

7 Flue Gas Pressure 0.97 atm

8 Flue Gas Pressure 0.97 atm

9 Flue Gas Pressure 0.96 atm

1 Standard Pressure 1 atm

10 Standard Pressure 1 atm

11 Standard Pressure 1 atm

Tuesday, February 01, 2011 Page 30 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

12 Standard Pressure 1 atm

4 Standard Pressure 1 atm

5 Standard Pressure 1 atm

6 Standard Pressure 1 atm

7 Standard Pressure 1 atm

8 Standard Pressure 1 atm

9 Standard Pressure 1 atm

1 Standard Temperature 68 Deg F

10 Standard Temperature 68 Deg F

11 Standard Temperature 68 Deg F

12 Standard Temperature 68 Deg F

4 Standard Temperature 68 Deg F

5 Standard Temperature 68 Deg F

6 Standard Temperature 68 Deg F

7 Standard Temperature 68 Deg F

8 Standard Temperature 68 Deg F

9 Standard Temperature 68 Deg F

1 Unit Gross Electrical Output 335 Mwe

10 Unit Gross Electrical Output 393 Mwe

11 Unit Gross Electrical Output 393 Mwe

12 Unit Gross Electrical Output 393 Mwe

4 Unit Gross Electrical Output 330 Mwe

5 Unit Gross Electrical Output 330 Mwe

6 Unit Gross Electrical Output 330 Mwe

7 Unit Gross Electrical Output 395 Mwe

8 Unit Gross Electrical Output 394 Mwe

9 Unit Gross Electrical Output 393 Mwe

1 Unit Net Electric Generation 309 MWh

10 Unit Net Electric Generation 374 MWh

11 Unit Net Electric Generation 375 MWh

12 Unit Net Electric Generation 375 MWh

4 Unit Net Electric Generation 305 MWh

5 Unit Net Electric Generation 306 MWh

6 Unit Net Electric Generation 307 MWh

7 Unit Net Electric Generation 377 MWh

8 Unit Net Electric Generation 376 MWh

Tuesday, February 01, 2011 Page 31 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

9 Unit Net Electric Generation 374 MWh

1 0

10 0

11 0

12 0

4 0

5 0

6 0

7 0

8 0

9 0

1 0

10 0

11 0

12 0

4 0

5 0

6 0

7 0

8 0

9 0

1 ESP Status 0 i/s or o/s

10 ESP Status 0 i/s or o/s

11 ESP Status 0 i/s or o/s

12 ESP Status 0 i/s or o/s

4 ESP Status 0 i/s or o/s

5 ESP Status 0 i/s or o/s

6 ESP Status 0 i/s or o/s

7 ESP Status 0 i/s or o/s

8 ESP Status 0 i/s or o/s

9 ESP Status 0 i/s or o/s

1 Baghouse Status 0 i/s or o/s

10 Baghouse Status 0 i/s or o/s

11 Baghouse Status 0 i/s or o/s

12 Baghouse Status 0 i/s or o/s

4 Baghouse Status 0 i/s or o/s

Tuesday, February 01, 2011 Page 32 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

APCD Run Data

Process Lab Run Data

5 Baghouse Status 0 i/s or o/s

6 Baghouse Status 0 i/s or o/s

7 Baghouse Status 0 i/s or o/s

8 Baghouse Status 0 i/s or o/s

9 Baghouse Status 0 i/s or o/s

1 0

1 0

Run Name Value UOM Comments

Target

Value

1 BAGHOUSE 0 0

1 ELECTROSTATIC PRECIPITATOR 0 0

1 FLUE GAS DESULFURIZATION 0 0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 0 Btu/lb

1 Fuel Moisture 0 %

1 Fuel Mercury Content 0 ppm

1 Fuel Cadmium Content 0 ppm

1 Ultimate/Proximate Analysis 0

1 Fuel Nickel Content 0 ppm

1 Fuel Arsenic Content 0 ppm

1 Fuel Chromium Content 0 ppm

1 Fuel Beryllium Content 0 ppm

1 Fuel Lead Content 0 ppm

1 Fuel Manganese Content 0 ppm

1 Fuel Chlorine Content 0 ppm

1 Fuel Fluorine Content 0 ppm

Tuesday, February 01, 2011 Page 33 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Sampling / Stack Data Results Detail

Location Stack Exit - Method 26A

Average

Run Number M26A-2 M26A-3 M26A-4

Test Date 4/21/2010 4/21/2010 4/21/2010

Run Start Time 3:10:00 PM 5:00:00 PM 6:40:00 PM

Run Finish Time 4:32:00 PM 6:20:00 PM 7:58:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 60 60 60

Nozzle Diameter, inches 0.219 0.219 0.219 0.219

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1 1 1 1.000

Barometric Pressure, inches of Mercury 29.78 29.77 29.77 29.773

Average Orifice Meter Differential, inches H2O 1.06 1.08 1.11 1.083

Dry Gas Meter Volume Sampled, cubic feet 34.182 34.381 34.745 34.436

Average Dry Gas Meter Temperature, °F 81.69 80.85 81.69 81.410

Dry Gas Meter Volume Sampled, dscf 33.249 33.485 33.789 33.508

Total Moisture Liquid collected, g 189.6 170.3 181.7 180.533

Volume of Water Vapor, standard cubic feet 8.92 8.02 8.55 8.497

Moisture Content of Stack Gas, % 21.15 19.32 20.19 20.220

Moisture Saturation at Stack Gas Temperature, % 14.07 14.13 14.28 14.160

Dry Mole Fraction 0.8593 0.8587 0.8572 0.858

Carbon Dioxide, % 13.34 13.43 12.99 13.253

Oxygen, % 5.73 5.69 5.45 5.623

Carbon Monoxide & Nitrogen, % 80.93 80.88 81.56 81.123

Fuel Factor 1.14 1.13 1.19

Dry Molecular Weight, lb/lb-Mole 30.36 30.38 30.30 30.347

Wet Molecular weight, lb/lb-Mole 29.90 29.56 29.61 29.690

Flue Gas Static Pressure, inches of H2O -0.45 -0.45 -0.45 -0.450

Absolute Flue Gas Pressure, inches of Mercury 29.75 29.74 29.74 29.743

Average Stack Gas Temperature, °F 127.15 127.31 127.69 127.383

Average Velocity Head, inches of H2O 0.5524992177

89829

0.568683778

914407

0.583894436

415868

0.568

Average Stack Gas Velocity, feet/second 43.37 44.26 44.83 44.153

Stack Cross-Sectional Area, square feet 738.623 738.623 738.623 738.623

Dry Volumetric Flow Rate, dry scfm 1,476,789.3 1,505,126.0 1,520,862.6 1,500,925.9

67

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,922,044.8 1,961,487.2 1,986,748.1 1,956,760.0

33

Percent Isokinetic of Sampling Rate, % 106.0 104.7 104.6 105.100

Percent Excess Air, % 36.6 36.3 33.9 35.600

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 368 368 368

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Tuesday, February 01, 2011 Page 34 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Tuesday, February 01, 2011 Page 35 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Location Stack Exit - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Tuesday, February 01, 2011 Page 36 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Tuesday, February 01, 2011 Page 37 of 38
PPL Generation, LLC - Brunner Island Station Units 1/2

Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Tuesday, February 01, 2011 Page 38 of 38