Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Monday, March 07, 2011 Page 1 of 22
Facility Information:

Costa Sur CS6

Carr. 165

Guayanilla PR

Contact: Arsenio Reyes

Phone: 787-521-4988

Fax: Of above person

Email: Of above person

Testing Company:

URS Corporation

1600 Perimeter Park Drive

Morrisville NC 27560

Contact:Richard McMillan

Phone: 919-461-1217

Fax: Of above person

Email: richard_mcmillan@urscorp.com

Air Permit Number:

PR4

Permitted Source ID/Name:

CS6 Enter the Boiler ID of the tested boiler (left)

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

This description should describe the process and associated controls to differentiate this facility from, or document 

similarity with others of same SCC.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: Enter ARS ID FRS #: Enter FRS ID

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 0 0 0 0 0 0 0 0

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit % H2O Method 1 - 4 3 180 0

Stack Exit Carbon Monoxide Method 10 3 120 0

Stack Exit Formaldehyde Method 0011 3 120 0

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Monday, March 07, 2011 Page 2 of 22
Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Other TCDD Method 23 0

Stack Exit Other PeCDD Method 23 0

Stack Exit Other HxCDD Method 23 0

Stack Exit Other HpCDD Method 23 0

Stack Exit Other TCDF Method 23 0

Stack Exit Other PeCDF Method 23 0

Stack Exit Other HxCDF Method 23 0

Stack Exit Other HpCDF Method 23 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Stack Exit Total PCBs Method 23 3 480 0

Stack Exit Total TEQ Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 120 0

Stack Exit Hydrogen Chloride Method 26 3 180 0

Stack Exit Hydrogen Fluoride Method 26 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 180 0

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Filterable PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Organic Condensible 

Particulate

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Monday, March 07, 2011 Page 3 of 22
The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

In this section, identify the promulgation date of any specified test method that you use for determining the 

procedures followed. This field is also used to document any modifications that are necessary to conduct the 

emissions test if they are outside the requirements of the cited method. If this modification was approved verbally by 

a regulatory agency, the name and date of approval should be included. Written formal approval should be attached 

to this file using the "Attach File" button. Test procedures that are different from those published in the Federal 

Register should be attached using the "Attach File" button.

Total PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Filterable Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Filterable Particulate Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Co2 Method 3A CO2 3 120 0

Stack Exit Co2 Method 3A CO2 3 240 0

Stack Exit O2 Method 3A O2 3 240 0

Stack Exit O2 Method 3A O2 3 480 0

Stack Exit Co2 Method 3A CO2 3 480 0

Stack Exit O2 Method 3A O2 3 120 0

Inorganic (Aqueous) 

Condensible Part.

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Organic Condensible 

Particulate

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Total Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Stack Exit Filterable Particulate Method 5 3 240 0

Filterable Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Stack Exit Sulfur Dioxide Method 6C 3 180 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0

Monday, March 07, 2011 Page 4 of 22
Sampling / Stack Data Results Summary

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 6/16/2010 6/17/2010 6/18/2010

Run Start Time 8:53:00 AM 9:45:00 

AM

8:53:00 AM

Run Finish Time 6:04:00 PM 7:31:00 PM 6:04:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 301.133 276.847 301.133 293.038

Moisture Content of Stack Gas, % 11.42 10.69 11.42 11.177

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 12.6 12.5 12.6 12.567

Oxygen, % 5 5.2 5 5.067

Average Stack Gas Temperature, °F 301.67 296.50 301.67 299.947

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 99.4 99.9 99.4 99.567

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, March 07, 2011 Page 5 of 22
Location Stack Exit - Method 29 

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes Stack Exit Stack Exit Stack Exit

Dry Gas Meter Volume Sampled, dscf 0.153 0.153 0.153 0.153

Moisture Content of Stack Gas, % 29.84 29.85 29.76 29.817

Moisture Saturation at Stack Gas Temperature, % 0.45 0.46 0.46 0.457

Carbon Dioxide, % 89.96 93.29 95.33 92.860

Oxygen, % 45.498 44.973 41.642 44.038

Average Stack Gas Temperature, °F 6.4 5.9 5 5.767

Dry Volumetric Flow Rate, dry scfm 310.00 307.29 307.65 308.313

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1.343523401

23616

1.27024763

159553

1.133735073

99612

1.249

Percent Isokinetic of Sampling Rate, % 78.91 76.41 72.27 75.863

F-Factor, dscfm/MMBtu @ %O2 0 0 0 0.000

Fw 0.000 0.000 0.000 0.000

Fc 0 0 0 0.000

Monday, March 07, 2011 Page 6 of 22
Emissions Summary

Location: Stack Exit - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000132 0.0000000077 0.0000000103 0.000

lb/mmBtuO2 1.17E-12 7.50E-13 9.11E-13 0.000

ng/dscm 1.55E-03 9.82E-04 1.21E-03 0.001

ng/dscm@7%O2 1.36E-03 8.69E-04 1.06E-03 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000084 0.0000000053 0.0000000051 0.000

lb/mmBtuO2 7.43E-13 5.16E-13 4.51E-13 0.000

ng/dscm 9.85E-04 6.76E-04 5.98E-04 0.001

ng/dscm@7%O2 8.61E-04 5.98E-04 5.23E-04 0.001

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000045 0.0000000057 0.0000000048 0.000

lb/mmBtuO2 3.98E-13 5.55E-13 4.25E-13 0.000

ng/dscm 5.28E-04 7.27E-04 5.63E-04 0.001

ng/dscm@7%O2 4.62E-04 6.44E-04 4.92E-04 0.001

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000001773 0.0000000025 0.0000000017 0.000

lb/mmBtuO2 1.57E-11 2.44E-13 1.50E-13 0.000

ng/dscm 2.08E-02 3.19E-04 1.99E-04 0.007

ng/dscm@7%O2 1.82E-02 2.82E-04 1.74E-04 0.006

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000039 0.0000000032 0.0000000018 0.000

lb/mmBtuO2 3.45E-13 3.12E-13 1.59E-13 0.000

ng/dscm 4.57E-04 4.08E-04 2.11E-04 0.000

ng/dscm@7%O2 4.00E-04 3.61E-04 1.84E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.0000000026 0.0000000018 0.000

lb/mmBtuO2 2.83E-13 2.53E-13 1.59E-13 0.000

ng/dscm 3.75E-04 3.32E-04 2.11E-04 0.000

ng/dscm@7%O2 3.28E-04 2.94E-04 1.84E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

Monday, March 07, 2011 Page 7 of 22
RunNumber 1 2 3

Mass_mg 0.0000000048 0.000000004 0.0000000017 0.000

lb/mmBtuO2 4.25E-13 3.90E-13 1.50E-13 0.000

ng/dscm 5.63E-04 5.10E-04 1.99E-04 0.000

ng/dscm@7%O2 4.92E-04 4.52E-04 1.74E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000034 0.0000000027 0.0000000018 0.000

lb/mmBtuO2 3.01E-13 2.63E-13 1.59E-13 0.000

ng/dscm 3.99E-04 3.44E-04 2.11E-04 0.000

ng/dscm@7%O2 3.49E-04 3.05E-04 1.84E-04 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000002 0.000000002 0.0000000019 0.000

lb/mmBtuO2 1.77E-13 1.95E-13 1.68E-13 0.000

ng/dscm 2.35E-04 2.55E-04 2.23E-04 0.000

ng/dscm@7%O2 2.05E-04 2.26E-04 1.95E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000036 0.0000000036 0.0000000028 0.000

lb/mmBtuO2 3.18E-13 3.51E-13 2.48E-13 0.000

ng/dscm 4.22E-04 4.59E-04 3.28E-04 0.000

ng/dscm@7%O2 3.69E-04 4.06E-04 2.87E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000003 0.0000000049 0.0000000026 0.000

lb/mmBtuO2 2.65E-13 4.77E-13 2.30E-13 0.000

ng/dscm 3.52E-04 6.25E-04 3.05E-04 0.000

ng/dscm@7%O2 3.08E-04 5.53E-04 2.67E-04 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.0000000538 0.0000000302 0.0000002223 0.000

lb/mmBtuO2 4.76E-12 2.94E-12 1.97E-11 0.000

ng/dscm 6.31E-03 3.85E-03 2.61E-02 0.012

ng/dscm@7%O2 5.52E-03 3.41E-03 2.28E-02 0.011

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.00000138617 0.00000060362 0.00000613904 0.000

lb/mmBtuO2 1.23E-10 5.88E-11 5.43E-10 0.000

ng/dscm 1.63E-01 7.70E-02 7.20E-01 0.320

ng/dscm@7%O2 1.42E-01 6.82E-02 6.29E-01 0.280

Monday, March 07, 2011 Page 8 of 22
Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.0000052663 0.00000240275 0.00002131948 0.000

lb/mmBtuO2 4.66E-10 2.34E-10 1.89E-09 0.000

ng/dscm 6.18E-01 3.07E-01 2.50E+00 1.142

ng/dscm@7%O2 5.40E-01 2.72E-01 2.19E+00 1.001

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.00000067746 0.00000029329 0.00000307175 0.000

lb/mmBtuO2 5.99E-11 2.86E-11 2.72E-10 0.000

ng/dscm 7.95E-02 3.74E-02 3.60E-01 0.159

ng/dscm@7%O2 6.95E-02 3.31E-02 3.15E-01 0.139

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.00000025867 0.00000013541 0.00000102012 0.000

lb/mmBtuO2 2.29E-11 1.32E-11 9.02E-11 0.000

ng/dscm 3.03E-02 1.73E-02 1.20E-01 0.056

ng/dscm@7%O2 2.65E-02 1.53E-02 1.05E-01 0.049

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.0000141047 0.0000066382 0.0000570141 0.000

lb/mmBtuO2 1.25E-09 6.47E-10 5.04E-09 0.000

ng/dscm 1.65E+00 8.47E-01 6.69E+00 3.062

ng/dscm@7%O2 1.44E+00 7.50E-01 5.85E+00 2.680

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.00000049219 0.00000023194 0.00000181191 0.000

lb/mmBtuO2 4.35E-11 2.26E-11 1.60E-10 0.000

ng/dscm 5.77E-02 2.96E-02 2.13E-01 0.100

ng/dscm@7%O2 5.04E-02 2.62E-02 1.86E-01 0.088

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000039 0.0000000037 0.0000000017 0.000

lb/mmBtuO2 3.45E-13 3.60E-13 1.50E-13 0.000

ng/dscm 4.57E-04 4.72E-04 1.99E-04 0.000

ng/dscm@7%O2 4.00E-04 4.18E-04 1.74E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000077 0.0000000072 0.0000000036 0.000

lb/mmBtuO2 6.81E-13 7.01E-13 3.18E-13 0.000

Monday, March 07, 2011 Page 9 of 22
ng/dscm 9.03E-04 9.19E-04 4.22E-04 0.001

ng/dscm@7%O2 7.89E-04 8.14E-04 3.69E-04 0.001

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000027 0.0000000025 0.0000000023 0.000

lb/mmBtuO2 2.39E-13 2.44E-13 2.03E-13 0.000

ng/dscm 3.17E-04 3.19E-04 2.70E-04 0.000

ng/dscm@7%O2 2.77E-04 2.82E-04 2.36E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000026 0.0000000033 0.0000000031 0.000

lb/mmBtuO2 2.30E-13 3.21E-13 2.74E-13 0.000

ng/dscm 3.05E-04 4.21E-04 3.64E-04 0.000

ng/dscm@7%O2 2.67E-04 3.73E-04 3.18E-04 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.00000001586 0.00000001126 0.00000006164 0.000

lb/mmBtuO2 1.40E-12 1.10E-12 5.45E-12 0.000

ng/dscm 1.86E-03 1.44E-03 7.23E-03 0.004

ng/dscm@7%O2 1.63E-03 1.27E-03 6.32E-03 0.003

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.00000062637 0.00000025637 0.00000289642 0.000

lb/mmBtuO2 5.54E-11 2.50E-11 2.56E-10 0.000

ng/dscm 7.35E-02 3.27E-02 3.40E-01 0.149

ng/dscm@7%O2 6.43E-02 2.90E-02 2.97E-01 0.130

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.00000529663 0.00000231531 0.00002455616 0.000

lb/mmBtuO2 4.68E-10 2.26E-10 2.17E-09 0.000

ng/dscm 6.21E-01 2.95E-01 2.88E+00 1.265

ng/dscm@7%O2 5.43E-01 2.61E-01 2.52E+00 1.108

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.00000024353 0.00000010789 0.00000107416 0.000

lb/mmBtuO2 2.15E-11 1.05E-11 9.50E-11 0.000

ng/dscm 2.86E-02 1.38E-02 1.26E-01 0.056

ng/dscm@7%O2 2.50E-02 1.22E-02 1.10E-01 0.049

Compound: OCDD

Average

RunNumber 1 2 3

Monday, March 07, 2011 Page 10 of 22
Mass_mg 0.0000000881 0.0000000507 0.0000000673 0.000

lb/mmBtuO2 7.79E-12 4.94E-12 5.95E-12 0.000

ng/dscm 1.03E-02 6.47E-03 7.89E-03 0.008

ng/dscm@7%O2 9.00E-03 5.73E-03 6.90E-03 0.007

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000017 0.0000000095 0.0000000131 0.000

lb/mmBtuO2 1.50E-12 9.26E-13 1.16E-12 0.000

ng/dscm 1.99E-03 1.21E-03 1.54E-03 0.002

ng/dscm@7%O2 1.74E-03 1.07E-03 1.35E-03 0.001

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000162 0.0000000126 0.0000000221 0.000

lb/mmBtuO2 1.43E-12 1.23E-12 1.95E-12 0.000

ng/dscm 1.90E-03 1.61E-03 2.59E-03 0.002

ng/dscm@7%O2 1.66E-03 1.43E-03 2.26E-03 0.002

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000048 0 0 0.000

lb/mmBtuO2 4.25E-13 0.00E+00 0.00E+00 0.000

ng/dscm 5.63E-04 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 4.92E-04 0.00E+00 0.00E+00 0.000

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000176 0.0000000118 0.0000000356 0.000

lb/mmBtuO2 1.56E-12 1.15E-12 3.15E-12 0.000

ng/dscm 2.06E-03 1.51E-03 4.18E-03 0.003

ng/dscm@7%O2 1.80E-03 1.34E-03 3.65E-03 0.002

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000109 0.0000000073 0.0000000032 0.000

lb/mmBtuO2 9.64E-13 7.11E-13 2.83E-13 0.000

ng/dscm 1.28E-03 9.31E-04 3.75E-04 0.001

ng/dscm@7%O2 1.12E-03 8.24E-04 3.28E-04 0.001

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000131 0.0000000085 0.0000000375 0.000

lb/mmBtuO2 1.16E-12 8.28E-13 3.32E-12 0.000

ng/dscm 1.54E-03 1.08E-03 4.40E-03 0.002

ng/dscm@7%O2 1.35E-03 9.56E-04 3.85E-03 0.002

Monday, March 07, 2011 Page 11 of 22
Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000362 0.0000000318 0 0.000

lb/mmBtuO2 3.20E-12 3.10E-12 0.00E+00 0.000

ng/dscm 4.25E-03 4.06E-03 0.00E+00 0.003

ng/dscm@7%O2 3.72E-03 3.59E-03 0.00E+00 0.002

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000265 0.0000000234 0.0000000606 0.000

lb/mmBtuO2 2.34E-12 2.28E-12 5.36E-12 0.000

ng/dscm 3.11E-03 2.99E-03 7.11E-03 0.004

ng/dscm@7%O2 2.72E-03 2.65E-03 6.22E-03 0.004

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000001116 0.0000000853 0.0000000183 0.000

lb/mmBtuO2 9.87E-12 8.31E-12 1.62E-12 0.000

ng/dscm 1.31E-02 1.09E-02 2.15E-03 0.009

ng/dscm@7%O2 1.15E-02 9.65E-03 1.88E-03 0.008

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0.0000002915 0.000000072197 0.00000008807 0.000

lb/mmBtuO2 2.58E-11 7.03E-12 7.79E-12 0.000

ng/dscm 3.42E-02 9.21E-03 1.03E-02 0.018

ng/dscm@7%O2 2.99E-02 8.15E-03 9.00E-03 0.016

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0.0000000577 0.000000048965 0.00000003931 0.000

lb/mmBtuO2 5.10E-12 4.77E-12 3.48E-12 0.000

ng/dscm 6.77E-03 6.25E-03 4.61E-03 0.006

ng/dscm@7%O2 5.92E-03 5.53E-03 4.03E-03 0.005

Compound: Total PCBs

Average

RunNumber 1 2 3

Mass_mg 0.0000284217 0.0000130262 0.0001191871 0.000

lb/mmBtuO2 2.51E-09 1.27E-09 1.05E-08 0.000

ng/dscm 3.33E+00 1.66E+00 1.40E+01 6.330

ng/dscm@7%O2 2.91E+00 1.47E+00 1.22E+01 5.527

Compound: Total TEQ

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

Monday, March 07, 2011 Page 12 of 22
ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Location: Stack Exit - Method 29 

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.0214 0.01619 0.019847 0.019

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 4.02E-06 3.27E-06 3.76E-06 0.000

mg/dscm 5.20E-03 4.25E-03 5.01E-03 0.005

mg/dscm@7%O2 4.66E-03 3.79E-03 4.35E-03 0.004

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.035 0.02748 0.0328 0.032

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 6.58E-06 5.54E-06 6.21E-06 0.000

mg/dscm 8.50E-03 7.21E-03 8.29E-03 0.008

mg/dscm@7%O2 7.62E-03 6.42E-03 7.20E-03 0.007

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.0014 0.001125 0.001412 0.001

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 2.63E-07 2.27E-07 2.67E-07 0.000

mg/dscm 3.40E-04 2.95E-04 3.57E-04 0.000

mg/dscm@7%O2 3.05E-04 2.63E-04 3.10E-04 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.0003 0.00036 0.00031 0.000

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 5.64E-08 7.26E-08 5.87E-08 0.000

mg/dscm 7.29E-05 9.45E-05 7.83E-05 0.000

mg/dscm@7%O2 6.54E-05 8.42E-05 6.80E-05 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.027 0.01858 0.02068 0.022

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 5.07E-06 3.75E-06 3.91E-06 0.000

mg/dscm 6.56E-03 4.88E-03 5.22E-03 0.006

mg/dscm@7%O2 5.88E-03 4.35E-03 4.53E-03 0.005

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 139.4 108.9 131.2 126.500

Monday, March 07, 2011 Page 13 of 22
Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 2.62E-02 2.20E-02 2.48E-02 0.024

mg/dscm 3.39E+01 2.86E+01 3.31E+01 31.867

mg/dscm@7%O2 3.04E+01 2.55E+01 2.88E+01 28.233

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.0181 0.01339 0.01603 0.016

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 3.40E-06 2.70E-06 3.03E-06 0.000

mg/dscm 4.40E-03 3.52E-03 4.05E-03 0.004

mg/dscm@7%O2 3.95E-03 3.14E-03 3.52E-03 0.004

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.283 0.229072 0.273652 0.262

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 5.32E-05 4.62E-05 5.18E-05 0.000

mg/dscm 6.88E-02 6.01E-02 6.91E-02 0.066

mg/dscm@7%O2 6.17E-02 5.36E-02 6.00E-02 0.058

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 2.5704 1.97611 2.32351 2.290

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 4.83E-04 3.99E-04 4.40E-04 0.000

mg/dscm 6.25E-01 5.19E-01 5.87E-01 0.577

mg/dscm@7%O2 5.60E-01 4.62E-01 5.10E-01 0.511

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0105 0.00811 0.01841 0.012

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 1.97E-06 1.64E-06 3.49E-06 0.000

mg/dscm 2.55E-03 2.13E-03 4.65E-03 0.003

mg/dscm@7%O2 2.29E-03 1.90E-03 4.04E-03 0.003

Location: Stack Exit - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 144.3 34.8 10.8 63.300

lb/mmBtuO2 9.26E-02 2.18E-02 6.91E-03 0.040

Monday, March 07, 2011 Page 14 of 22
Process Run Data

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 3.3 3.3 5.9 4.167

lb/mmBtuO2 2.12E-03 2.07E-03 3.77E-03 0.003

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 28.6 14.2 26.7 23.167

lb/mmBtuO2 1.84E-02 8.91E-03 1.71E-02 0.015

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 223 89.3 76.4 129.567

lb/mmBtuO2 1.43E-01 5.61E-02 4.89E-02 0.083

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 78.7 54.5 65.6 66.267

lb/mmBtuO2 5.05E-02 3.42E-02 4.20E-02 0.042

Monday, March 07, 2011 Page 15 of 22
Process Run Data

Run Name Value UOM Comments

Target

Value

1 Residual Oil (No. 6) Burned 1000 Gallons/million BTU using O2 164.3 0

2 Residual Oil (No. 6) Burned 1000 Gallons/million BTU using O2 159.9 0

3 Residual Oil (No. 6) Burned 1000 Gallons/million BTU using O2 165.2 0

4 Residual Oil (No. 6) Burned 1000 Gallons/million BTU using O2 177.6 0

5 Residual Oil (No. 6) Burned 1000 Gallons/million BTU using O2 173 0

1 Average Heat Input 3086.2 MMBtu/hr 0

2 Average Heat Input 3003.6 MMBtu/hr 0

3 Average Heat Input 3103.1 MMBtu/hr 0

4 Average Heat Input 3336 MMBtu/hr 0

5 Average Heat Input 3249.6 MMBtu/hr 0

1 Steam Output 2021 1000 lb steam/hr 0

2 Steam Output 1928 1000 lb steam/hr 0

3 Steam Output 2064 1000 lb steam/hr 0

4 Steam Output 2246 1000 lb steam/hr 0

5 Steam Output 2043 1000 lb steam/hr 0

1 Synfuel Firing Rate 0 0

2 Synfuel Firing Rate 0 0

3 Synfuel Firing Rate 0 0

4 Synfuel Firing Rate 0 0

5 Synfuel Firing Rate 0 0

1 Petroleum Coke Firing Rate 0 0

2 Petroleum Coke Firing Rate 0 0

3 Petroleum Coke Firing Rate 0 0

4 Petroleum Coke Firing Rate 0 0

5 Petroleum Coke Firing Rate 0 0

1 Coal Gas Firing Rate 0 0

2 Coal Gas Firing Rate 0 0

3 Coal Gas Firing Rate 0 0

4 Coal Gas Firing Rate 0 0

5 Coal Gas Firing Rate 0 0

1 Fuel Oil Firing Rate 0 0

2 Fuel Oil Firing Rate 0 0

3 Fuel Oil Firing Rate 0 0

Monday, March 07, 2011 Page 16 of 22
4 Fuel Oil Firing Rate 0 0

5 Fuel Oil Firing Rate 0 0

1 Flue Gas Flow Rate 0 dscfm 0

2 Flue Gas Flow Rate 0 dscfm 0

3 Flue Gas Flow Rate 0 dscfm 0

4 Flue Gas Flow Rate 0 dscfm 0

5 Flue Gas Flow Rate 0 dscfm 0

1 Pressure Drop Across FGD (if applicable) 0 in H20 0

2 Pressure Drop Across FGD (if applicable) 0 in H20 0

3 Pressure Drop Across FGD (if applicable) 0 in H20 0

4 Pressure Drop Across FGD (if applicable) 0 in H20 0

5 Pressure Drop Across FGD (if applicable) 0 in H20 0

1 FGD Scrubber Liquor pH 0 pH 0

2 FGD Scrubber Liquor pH 0 pH 0

3 FGD Scrubber Liquor pH 0 pH 0

4 FGD Scrubber Liquor pH 0 pH 0

5 FGD Scrubber Liquor pH 0 pH 0

1 FGD Scrubber Liquor Flow Rate 0 gal/min 0

2 FGD Scrubber Liquor Flow Rate 0 gal/min 0

3 FGD Scrubber Liquor Flow Rate 0 gal/min 0

4 FGD Scrubber Liquor Flow Rate 0 gal/min 0

5 FGD Scrubber Liquor Flow Rate 0 gal/min 0

1 Sorbent Type and Sorbent Injection Rate (if 

applicable)

0 lb/hr 0

2 Sorbent Type and Sorbent Injection Rate (if 

applicable)

0 lb/hr 0

3 Sorbent Type and Sorbent Injection Rate (if 

applicable)

0 lb/hr 0

4 Sorbent Type and Sorbent Injection Rate (if 

applicable)

0 lb/hr 0

5 Sorbent Type and Sorbent Injection Rate (if 

applicable)

0 lb/hr 0

1 Flue Gas Oxygen Content 2 % 0

2 Flue Gas Oxygen Content 1.6 % 0

3 Flue Gas Oxygen Content 1.7 % 0

4 Flue Gas Oxygen Content 1.9 % 0

5 Flue Gas Oxygen Content 1.9 % 0

1 Flue Gas Carbon Dioxide Content 0 % 0

Monday, March 07, 2011 Page 17 of 22
2 Flue Gas Carbon Dioxide Content 0 % 0

3 Flue Gas Carbon Dioxide Content 0 % 0

4 Flue Gas Carbon Dioxide Content 0 % 0

5 Flue Gas Carbon Dioxide Content 0 % 0

1 Flue Gas Moisture Content 0 % 0

2 Flue Gas Moisture Content 0 % 0

3 Flue Gas Moisture Content 0 % 0

4 Flue Gas Moisture Content 0 % 0

5 Flue Gas Moisture Content 0 % 0

1 Flue Gas Sampling Point Temperature 0 Deg F 0

2 Flue Gas Sampling Point Temperature 0 Deg F 0

3 Flue Gas Sampling Point Temperature 0 Deg F 0

4 Flue Gas Sampling Point Temperature 0 Deg F 0

5 Flue Gas Sampling Point Temperature 0 Deg F 0

1 Flue Gas Pressure 0 atm 0

2 Flue Gas Pressure 0 atm 0

3 Flue Gas Pressure 0 atm 0

4 Flue Gas Pressure 0 atm 0

5 Flue Gas Pressure 0 atm 0

1 Standard Pressure 0 atm 0

2 Standard Pressure 0 atm 0

3 Standard Pressure 0 atm 0

4 Standard Pressure 0 atm 0

5 Standard Pressure 0 atm 0

1 Standard Temperature 0 Deg F 0

2 Standard Temperature 0 Deg F 0

3 Standard Temperature 0 Deg F 0

4 Standard Temperature 0 Deg F 0

5 Standard Temperature 0 Deg F 0

1 Unit Gross Electrical Output 340 MW 0

2 Unit Gross Electrical Output 327 MW 0

3 Unit Gross Electrical Output 344 MW 0

4 Unit Gross Electrical Output 363 MW 0

5 Unit Gross Electrical Output 356 MW 0

1 Unit Net Electric Generation 0 MWh 0

2 Unit Net Electric Generation 0 MWh 0

Monday, March 07, 2011 Page 18 of 22
APCD Run Data

Process Lab Run Data

3 Unit Net Electric Generation 0 MWh 0

4 Unit Net Electric Generation 0 MWh 0

5 Unit Net Electric Generation 0 MWh 0

Run Name Value UOM Comments

Target

Value

1 List all emissions control devices in order of 

process flow. Choose from

0 0

1 drop down lists. If not on list add description and 

provide detailed

0 0

1 desription in section 5a. 0 0

Run Name Value UOM Comments

1 See 4b Comments. 0

Monday, March 07, 2011 Page 19 of 22
Sampling / Stack Data Results Detail

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 6/16/2010 6/17/2010 6/18/2010

Run Start Time 8:53:00 AM 9:45:00 AM 8:53:00 AM

Run Finish Time 6:04:00 PM 7:31:00 PM 6:04:00 PM

Net Traversing Points 49 49 49

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.22 0.22 0.22 0.220

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.032 1.032 1.032 1.032

Barometric Pressure, inches of Mercury 29.8 29.85 29.8 29.817

Average Orifice Meter Differential, inches H2O 1.42 1.17 1.42 1.337

Dry Gas Meter Volume Sampled, cubic feet 315.746 281.352 315.746 304.281

Average Dry Gas Meter Temperature, °F 111.04 94.06 111.04 105.380

Dry Gas Meter Volume Sampled, dscf 301.133 276.847 301.133 293.038

Total Moisture Liquid collected, g 825.2 703.8 825.2 784.733

Volume of Water Vapor, standard cubic feet 38.84 33.13 38.84 36.937

Moisture Content of Stack Gas, % 11.42 10.69 11.42 11.177

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8858 0.8931 0.8858 0.888

Carbon Dioxide, % 12.6 12.5 12.6 12.567

Oxygen, % 5 5.2 5 5.067

Carbon Monoxide & Nitrogen, % 82.4 82.3 82.4 82.367

Fuel Factor 1.26 1.26 1.26

Dry Molecular Weight, lb/lb-Mole 30.22 30.21 30.22 30.217

Wet Molecular weight, lb/lb-Mole 28.82 28.90 28.82 28.847

Flue Gas Static Pressure, inches of H2O 0.2 0.2 0.2 0.200

Absolute Flue Gas Pressure, inches of Mercury 29.81 29.86 29.81 29.827

Average Stack Gas Temperature, °F 301.67 296.50 301.67 299.947

Average Velocity Head, inches of H2O 0.9272984167

81937

0.760113675

222032

0.927298416

781938

0.872

Average Stack Gas Velocity, feet/second 65.11 58.62 65.11 62.947

Stack Cross-Sectional Area, square feet 0.000 0.000 0.000 0.000

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 99.4 99.9 99.4 99.567

Percent Excess Air, % 29.8 31.5 29.8 30.367

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 0 0 0

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, March 07, 2011 Page 20 of 22
Location Stack Exit - Method 29 

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, March 07, 2011 Page 21 of 22
Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes Stack Exit Stack Exit Stack Exit

Nozzle Diameter, inches 8/18/2010 8/18/2010 8/19/2010

Pitot Tube Coefficient OTM - 27/28 OTM - 27/28 OTM - 27/28

Dry Gas Meter Calibration Factor 1 2 3 2.000

Barometric Pressure, inches of Mercury 10:30:00 AM 9:30:00 AM 12:00:00 PM

Average Orifice Meter Differential, inches H2O 1:16:00 PM 2:58:15 PM 3:45:00 PM

Dry Gas Meter Volume Sampled, cubic feet 25 24 24 24.333

Average Dry Gas Meter Temperature, °F 150 120 115 128.333

Dry Gas Meter Volume Sampled, dscf 0.153 0.153 0.153 0.153

Total Moisture Liquid collected, g 0.84 0.84 0.84 0.840

Volume of Water Vapor, standard cubic feet 1.0039 1.0039 1.0039 1.004

Moisture Content of Stack Gas, % 29.84 29.85 29.76 29.817

Moisture Saturation at Stack Gas Temperature, % 0.45 0.46 0.46 0.457

Dry Mole Fraction 47.280 47.001 43.812 46.031

Carbon Dioxide, % 89.96 93.29 95.33 92.860

Oxygen, % 45.498 44.973 41.642 44.038

Carbon Monoxide & Nitrogen, % 128 118.6 118.1 121.567

Fuel Factor 6.02 5.58 5.56

Dry Molecular Weight, lb/lb-Mole 11.69 11.04 11.78 11.503

Wet Molecular weight, lb/lb-Mole 100.00 100.00 100.00 100.000

Flue Gas Static Pressure, inches of H2O 0.8831 0.8896 0.8822 0.885

Absolute Flue Gas Pressure, inches of Mercury 11.6 12 12.7 12.100

Average Stack Gas Temperature, °F 6.4 5.9 5 5.767

Average Velocity Head, inches of H2O 82 82.1 82.3 82.133

Average Stack Gas Velocity, feet/second 1.25 1.25 1.25 1.250

Stack Cross-Sectional Area, square feet 29.86 29.87 29.85 29.860

Dry Volumetric Flow Rate, dry scfm 310.00 307.29 307.65 308.313

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1.3435234012

3616

1.270247631

59553

1.133735073

99612

1.249

Percent Isokinetic of Sampling Rate, % 78.91 76.41 72.27 75.863

Percent Excess Air, % 0 0 0 0.000

F-Factor, dscfm/MMBtu @ %O2 0 0 0 0.000

Round Duct Diameter, inches 30.11 30.16 30.23

Rectangular Duct Width, inches 28.69 28.82 28.79

Rectangular Duct Length, inches 0.3 0.3 1.2

Fw 0.000 0.000 0.000 0.000

Fc 0 0 0 0.000

Monday, March 07, 2011 Page 22 of 22