Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Monday, February 07, 2011 Page 1 of 19
Facility Information:

James H Miller Jr

4250 Porter Road S.W.

Quinton Al 35130

Contact: Brandon Looney

Phone: 205-257-6162

Fax:

Email: MBLooney@southernco.com

Testing Company:

Weston Solutions

1625 Pumphrey Ave

Auburn Al 36832

Contact:Jon Howard

Phone: 334-466-5600

Fax: 334-466-5660

Email: j.howard@westonsolutions.com

Air Permit Number: Permitted Source ID/Name:

4 Unit 4

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rat

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

See Attached Report

Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information:

AFS #: FRS #:

SCC / Description

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack 300 0 0 0 2400 4380 4 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Carbon Monoxide Method 10 3 0

Stack Formaldehyde Method 0011 3 0

Total organic compounds 

(TOC) as Propane

Stack Method 25A 3 0

Stack Filterable PM2.5 OTM - 27 3 0

Organic Condensible 

Particulate

Stack OTM - 28 3 0

Monday, February 07, 2011 Page 2 of 19
The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

See Attached Report

Inorganic (Aqueous) 

Condensible Part.

Stack OTM - 28 3 0

Stack Manganese Method 29 3 0

Stack Nickel Method 29 3 0

Stack Filterable Particulate Method 29 3 0

Stack Lead Method 29 3 0

Stack Antimony Method 29 3 0

Stack Arsenic Method 29 3 0

Stack Cobalt Method 29 3 0

Stack Chromium Method 29 3 0

Stack Beryllium Method 29 3 0

Stack Cadmium Method 29 3 0

Stack Selenium Method 29 3 0

Stack O2 Method 3A O2 3 0

Stack Co2 Method 3A CO2 3 0

Monday, February 07, 2011 Page 3 of 19
Sampling / Stack Data Results Summary

Location Stack - Method 0011

Average

Run Number 1 2 3

Test Date 5/6/2010 5/6/2010 5/6/2010

Run Start Time 8:45:00 AM 11:10:00 

AM

1:34:00 PM

Run Finish Time 10:52:00 AM 1:18:00 PM 3:42:00 PM

Net Run Time, minutes 120 120 120

Dry Gas Meter Volume Sampled, dscf 73.585 73.515 71.912 73.004

Moisture Content of Stack Gas, % 11.94 11.96 11.79 11.897

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 13.4 13.4 13.5 13.433

Oxygen, % 6.3 6.3 6.2 6.267

Average Stack Gas Temperature, °F 300.71 309.00 312.57 307.427

Dry Volumetric Flow Rate, dry scfm 1,655,188.1 1,662,141.0 1,639,652.1 1,652,327.06

7

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,777,659.6 2,820,365.7 2,789,735.1 2,795,920.13

3

Percent Isokinetic of Sampling Rate, % 102.9 102.4 101.5 102.267

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Fw

Fc

Location Stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, February 07, 2011 Page 4 of 19
Location Stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Monday, February 07, 2011 Page 5 of 19
Location Stack - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, February 07, 2011 Page 6 of 19
Location Stack - OTM - 27

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack - OTM - 28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Monday, February 07, 2011 Page 7 of 19
Emissions Summary

Location: Stack - Method 0011

Compound: Formaldehyde

Average

RunNumber 1 2 3

Mass_mg 0.023 0.025 0.026 0.025

lb/mmBtuO2 9.69E-06 1.05E-05 1.11E-05 0.000

ppm 8.84E-03 9.62E-03 1.02E-02 0.010

ppm@7%O2 8.42E-03 9.16E-03 9.64E-03 0.009

Location: Stack - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 4.56E-01 5.42E-01 5.81E-01 0.526

ppm 4.46E+02 5.30E+02 5.68E+02 514.667

ppm@7%O2 4.25E+02 5.05E+02 5.41E+02 490.333

Location: Stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 3.25E-04 3.25E-04 8.06E-04 0.000

ppm 2.02E-01 2.02E-01 5.04E-01 0.303

ppm@7%O2 1.92E-01 1.92E-01 4.77E-01 0.287

Location: Stack - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.0028 0.0028 0.0028 0.003

lb/mmBtuO2 3.83E-07 3.85E-07 3.88E-07 0.000

mg/dscm 4.30E-04 4.36E-04 4.42E-04 0.000

mg/dscm@7%O2 4.15E-04 4.18E-04 4.21E-04 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.00295 0.00304 0.00322 0.003

lb/mmBtuO2 4.03E-07 4.18E-07 4.46E-07 0.000

mg/dscm 4.53E-04 4.73E-04 5.08E-04 0.000

mg/dscm@7%O2 4.37E-04 4.53E-04 4.84E-04 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.0007 0.0007 0.0007 0.001

lb/mmBtuO2 9.57E-08 9.62E-08 9.69E-08 0.000

mg/dscm 1.08E-04 1.09E-04 1.10E-04 0.000

mg/dscm@7%O2 1.04E-04 1.04E-04 1.05E-04 0.000

Monday, February 07, 2011 Page 8 of 19
Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.0007 0.0007 0.0007 0.001

lb/mmBtuO2 9.57E-08 9.62E-08 9.69E-08 0.000

mg/dscm 1.08E-04 1.09E-04 1.10E-04 0.000

mg/dscm@7%O2 1.04E-04 1.04E-04 1.05E-04 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.00394 0.00252 0.00242 0.003

lb/mmBtuO2 5.38E-07 3.46E-07 3.35E-07 0.000

mg/dscm 6.05E-04 3.92E-04 3.82E-04 0.000

mg/dscm@7%O2 5.84E-04 3.76E-04 3.64E-04 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.00086 0.0009 0.0009 0.001

lb/mmBtuO2 1.18E-07 1.24E-07 1.25E-07 0.000

mg/dscm 1.32E-04 1.40E-04 1.42E-04 0.000

mg/dscm@7%O2 1.27E-04 1.34E-04 1.35E-04 0.000

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 10.6 9.5 17.4 12.500

lb/mmBtuO2 1.45E-03 1.31E-03 2.41E-03 0.002

mg/dscm 1.63E+00 1.48E+00 2.75E+00 1.953

mg/dscm@7%O2 1.57E+00 1.42E+00 2.62E+00 1.870

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.00312 0.00276 0.0023 0.003

lb/mmBtuO2 4.26E-07 3.79E-07 3.18E-07 0.000

mg/dscm 4.79E-04 4.29E-04 3.63E-04 0.000

mg/dscm@7%O2 4.62E-04 4.11E-04 3.46E-04 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.021 0.0098 0.0082 0.013

lb/mmBtuO2 2.87E-06 1.35E-06 1.14E-06 0.000

mg/dscm 3.23E-03 1.52E-03 1.29E-03 0.002

mg/dscm@7%O2 3.12E-03 1.46E-03 1.23E-03 0.002

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.01978 0.0035 0.0132 0.012

lb/mmBtuO2 2.70E-06 4.81E-07 1.83E-06 0.000

Monday, February 07, 2011 Page 9 of 19
Process Run Data

mg/dscm 3.04E-03 5.44E-04 2.08E-03 0.002

mg/dscm@7%O2 2.93E-03 5.21E-04 1.98E-03 0.002

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.1398 0.0927 0.085 0.106

lb/mmBtuO2 1.91E-05 1.27E-05 1.18E-05 0.000

mg/dscm 2.15E-02 1.44E-02 1.34E-02 0.016

mg/dscm@7%O2 2.08E-02 1.38E-02 1.28E-02 0.016

Location: Stack - OTM - 27

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 3.5 2.4 4 3.300

lb/mmBtuO2 9.07E-04 6.03E-04 1.01E-03 0.001

Location: Stack - OTM - 28

Compound: Inorganic (Aqueous) Condensible P

Average

RunNumber 1 2 3

Mass_mg 41.2 15.2 14.7 23.700

lb/mmBtuO2 1.07E-02 3.82E-03 3.71E-03 0.006

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 4.9 7 7.2 6.367

lb/mmBtuO2 1.27E-03 1.76E-03 1.82E-03 0.002

Monday, February 07, 2011 Page 10 of 19
Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Gross Electric output (THC) 709.99 MW 0

1 Gross Electric output (Formaldehyde) 709.99 MW 0

1 Gross Electric output (OTM 27 and 28) 706.97 MW 0

1 Gross Electric Output (Metals and PM) 706.97 MW 0

Monday, February 07, 2011 Page 11 of 19
Sampling / Stack Data Results Detail

Location Stack - Method 0011

Average

Run Number 1 2 3

Test Date 5/6/2010 5/6/2010 5/6/2010

Run Start Time 8:45:00 AM 11:10:00 AM 1:34:00 PM

Run Finish Time 10:52:00 AM 1:18:00 PM 3:42:00 PM

Net Traversing Points 24 24 23

Net Run Time, minutes 120 120 120

Nozzle Diameter, inches 0.18 0.18 0.18 0.180

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.986 0.986 0.986 0.986

Barometric Pressure, inches of Mercury 29.35 29.35 29.35 29.350

Average Orifice Meter Differential, inches H2O 1.34 1.37 1.33 1.347

Dry Gas Meter Volume Sampled, cubic feet 79.164 79.949 78.521 79.211

Average Dry Gas Meter Temperature, °F 91.25 97.29 99.48 96.007

Dry Gas Meter Volume Sampled, dscf 73.585 73.515 71.912 73.004

Total Moisture Liquid collected, g 212 212.2 204.2 209.467

Volume of Water Vapor, standard cubic feet 9.98 9.99 9.61 9.860

Moisture Content of Stack Gas, % 11.94 11.96 11.79 11.897

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8806 0.8804 0.8821 0.881

Carbon Dioxide, % 13.4 13.4 13.5 13.433

Oxygen, % 6.3 6.3 6.2 6.267

Carbon Monoxide & Nitrogen, % 80.3 80.3 80.3 80.300

Fuel Factor 1.09 1.09 1.09

Dry Molecular Weight, lb/lb-Mole 30.40 30.40 30.41 30.403

Wet Molecular weight, lb/lb-Mole 28.92 28.92 28.95 28.930

Flue Gas Static Pressure, inches of H2O -2.5 -2.5 -2.5 -2.500

Absolute Flue Gas Pressure, inches of Mercury 29.17 29.17 29.17 29.170

Average Stack Gas Temperature, °F 300.71 309.00 312.57 307.427

Average Velocity Head, inches of H2O 1.9127665831

5807

1.950537099

46986

1.901667200

91467

1.922

Average Stack Gas Velocity, feet/second 94.31 95.76 94.72 94.930

Stack Cross-Sectional Area, square feet 490.874 490.874 490.874 490.874

Dry Volumetric Flow Rate, dry scfm 1,655,188.1 1,662,141.0 1,639,652.1 1,652,327.0

67

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,777,659.6 2,820,365.7 2,789,735.1 2,795,920.1

33

Percent Isokinetic of Sampling Rate, % 102.9 102.4 101.5 102.267

Percent Excess Air, % 42.3 42.3 41.3 41.967

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Round Duct Diameter, inches 300 300 300

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw

Fc

Monday, February 07, 2011 Page 12 of 19
Location Stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 07, 2011 Page 13 of 19
Location Stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 07, 2011 Page 14 of 19
Location Stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 07, 2011 Page 15 of 19
Location Stack - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 07, 2011 Page 16 of 19
Location Stack - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 07, 2011 Page 17 of 19
Location Stack - OTM - 27

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 07, 2011 Page 18 of 19
Location Stack - OTM - 28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 07, 2011 Page 19 of 19