### Name:

Title: Company: Sign Date: Name:
Title: Company: Sign Date: Permitted Facility Representative / Date Testing Company Representative / Date Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Monday, February 07, 2011 Page 1 of 19

### Facility Information:

James H Miller Jr

4250 Porter Road S.W.

Quinton Al 35130
Contact: Brandon Looney

Phone: 205-257-6162

Fax:

Email: MBLooney@southernco.com Testing Company:

Weston Solutions 1625 Pumphrey Ave

Auburn Al 36832
Contact: Jon Howard

Phone: 334-466-5600

Fax: 334-466-5660

Email: j.howard@westonsolutions.com

Air Permit Number: Permitted Source ID/Name:
Unit 4 4

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rat

Description of the source (including control equipment). Please see the attachments for source or process flow diagram:
See Attached Report Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information: AFS #: FRS #:

SCC / Description

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width

Stack 300 2400 4380 4 0 24 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location

Carbon Monoxide Method 10 3 0 Stack Formaldehyde Method 0011 3 0 Stack Total organic compounds

(TOC) as Propane Method 25A 3 0 Stack

Filterable PM2.5 OTM - 27 3 0 Stack Organic Condensible

Particulate OTM - 28 3 0 Stack



### Monday, February 07, 2011 Page 2 of 19

### The following describes any modifications and/or deviations to the applicable test

methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.
See Attached Report

Inorganic (Aqueous) Condensible Part. OTM - 28 3 0 Stack

Manganese Method 29 3 0 Stack Nickel Method 29 3 0 Stack
Filterable Particulate Method 29 3 0 Stack Lead Method 29 3 0 Stack Antimony Method 29 3 0 Stack Arsenic Method 29 3 0 Stack Cobalt Method 29 3 0 Stack Chromium Method 29 3 0 Stack Beryllium Method 29 3 0 Stack Cadmium Method 29 3 0 Stack Selenium Method 29 3 0 Stack
O2 Method 3A O2 3 0 Stack
Co2 Method 3A CO2 3 0 Stack



### Monday, February 07, 2011 Page 3 of 19

### Sampling / Stack Data Results Summary

Location Stack - Method 0011
Average
Run Number 1 2 3

Test Date 5/6/2010 5/6/2010 5/6/2010

Run Start Time 8:45:00 AM 11:10:00 AM 1:34:00 PM

Run Finish Time 10:52:00 AM 1:18:00 PM 3:42:00 PM
Net Run Time, minutes 120 120 120 Dry Gas Meter Volume Sampled, dscf 73.585 73.515 71.912 73.004
Moisture Content of Stack Gas, % 11.94 11.96 11.79 11.897 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000
Carbon Dioxide, % 13.4 13.4 13.5 13.433 Oxygen, % 6.3 6.3 6.2 6.267 Average Stack Gas Temperature, °F 300.71 309.00 312.57 307.427 Dry Volumetric Flow Rate, dry scfm 1,655,188.1 1,662,141.0 1,639,652.1 1,652,327.06 7
Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,777,659.6 2,820,365.7 2,789,735.1 2,795,920.13 3 Percent Isokinetic of Sampling Rate, % 102.9 102.4 101.5 102.267
F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Fw

Fc



### Location Stack - Method 10
Average
Run Number

Test Date

Run Start Time

Run Finish Time
Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm
F-Factor, dscfm/MMBtu @ %O2
Moisture, % Fuel Type

Fw

Fc



### Monday, February 07, 2011 Page 4 of 19

### Location Stack - Method 25A
Average

Run Number

Test Date

Run Start Time

Run Finish Time
Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm
F-Factor, dscfm/MMBtu @ %O2
Moisture, % Fuel Type

Fw

Fc



### Location Stack - Method 29
Average

Run Number

Test Date

Run Start Time

Run Finish Time
Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf
Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, %
Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm
Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, %
F-Factor, dscfm/MMBtu @ %O2

Fw

Fc



### Monday, February 07, 2011 Page 5 of 19

### Location Stack - Method 3A CO2
Average

Run Number

Test Date

Run Start Time

Run Finish Time
Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm
F-Factor, dscfm/MMBtu @ %O2
Moisture, % Fuel Type

Fw

Fc



### Location Stack - Method 3A O2
Average

Run Number

Test Date

Run Start Time

Run Finish Time
Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm
F-Factor, dscfm/MMBtu @ %O2
Moisture, % Fuel Type

Fw

Fc



### Monday, February 07, 2011 Page 6 of 19

### Location Stack - OTM - 27
Average

Run Number

Test Date

Run Start Time

Run Finish Time
Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf
Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, %
Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm
Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, %
F-Factor, dscfm/MMBtu @ %O2

Fw

Fc



### Location Stack - OTM - 28
Average
Run Number

Test Date

Run Start Time

Run Finish Time
Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf
Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, %
Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm
Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, %
F-Factor, dscfm/MMBtu @ %O2

Fw

Fc



### Monday, February 07, 2011 Page 7 of 19

### Emissions Summary

Location: Stack - Method 0011 Compound: Formaldehyde Average RunNumber 1 2 3 Mass_mg 0.023 0.025 0.026 0.025 lb/mmBtuO2 9.69E-06 1.05E-05 1.11E-05 0.000
ppm 8.84E-03 9.62E-03 1.02E-02 0.010 ppm@7%O2 8.42E-03 9.16E-03 9.64E-03 0.009



### Location: Stack - Method 10 

### Compound: Carbon Monoxide Average
Run 1 2 3 lb/mmBtuO2 4.56E-01 5.42E-01 5.81E-01 0.526
ppm 4.46E+02 5.30E+02 5.68E+02 514.667 ppm@7%O2 4.25E+02 5.05E+02 5.41E+02 490.333



### Location: Stack - Method 25A Compound: Total organic compounds (TOC) as Average
Run 1 2 3 lb/mmBtuO2 3.25E-04 3.25E-04 8.06E-04 0.000
ppm 2.02E-01 2.02E-01 5.04E-01 0.303 ppm@7%O2 1.92E-01 1.92E-01 4.77E-01 0.287



### Location: Stack - Method 29 Compound: Antimony Average RunNumber 1 2 3 Mass_mg 0.0028 0.0028 0.0028 0.003 lb/mmBtuO2 3.83E-07 3.85E-07 3.88E-07 0.000 mg/dscm 4.30E-04 4.36E-04 4.42E-04 0.000 mg/dscm@7%O2 4.15E-04 4.18E-04 4.21E-04 0.000



### Compound: Arsenic Average RunNumber 1 2 3 Mass_mg 0.00295 0.00304 0.00322 0.003 lb/mmBtuO2 4.03E-07 4.18E-07 4.46E-07 0.000 mg/dscm 4.53E-04 4.73E-04 5.08E-04 0.000 mg/dscm@7%O2 4.37E-04 4.53E-04 4.84E-04 0.000



### Compound: Beryllium Average RunNumber 1 2 3 Mass_mg 0.0007 0.0007 0.0007 0.001 lb/mmBtuO2 9.57E-08 9.62E-08 9.69E-08 0.000 mg/dscm 1.08E-04 1.09E-04 1.10E-04 0.000 mg/dscm@7%O2 1.04E-04 1.04E-04 1.05E-04 0.000



### Monday, February 07, 2011 Page 8 of 19

### Compound: Cadmium Average RunNumber 1 2 3 Mass_mg 0.0007 0.0007 0.0007 0.001 lb/mmBtuO2 9.57E-08 9.62E-08 9.69E-08 0.000 mg/dscm 1.08E-04 1.09E-04 1.10E-04 0.000 mg/dscm@7%O2 1.04E-04 1.04E-04 1.05E-04 0.000



### Compound: Chromium Average RunNumber 1 2 3 Mass_mg 0.00394 0.00252 0.00242 0.003 lb/mmBtuO2 5.38E-07 3.46E-07 3.35E-07 0.000 mg/dscm 6.05E-04 3.92E-04 3.82E-04 0.000 mg/dscm@7%O2 5.84E-04 3.76E-04 3.64E-04 0.000



### Compound: Cobalt Average RunNumber 1 2 3 Mass_mg 0.00086 0.0009 0.0009 0.001 lb/mmBtuO2 1.18E-07 1.24E-07 1.25E-07 0.000 mg/dscm 1.32E-04 1.40E-04 1.42E-04 0.000 mg/dscm@7%O2 1.27E-04 1.34E-04 1.35E-04 0.000



### Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 10.6 9.5 17.4 12.500 lb/mmBtuO2 1.45E-03 1.31E-03 2.41E-03 0.002 mg/dscm 1.63E+00 1.48E+00 2.75E+00 1.953 mg/dscm@7%O2 1.57E+00 1.42E+00 2.62E+00 1.870



### Compound: Lead Average RunNumber 1 2 3 Mass_mg 0.00312 0.00276 0.0023 0.003 lb/mmBtuO2 4.26E-07 3.79E-07 3.18E-07 0.000 mg/dscm 4.79E-04 4.29E-04 3.63E-04 0.000 mg/dscm@7%O2 4.62E-04 4.11E-04 3.46E-04 0.000



### Compound: Manganese Average RunNumber 1 2 3 Mass_mg 0.021 0.0098 0.0082 0.013 lb/mmBtuO2 2.87E-06 1.35E-06 1.14E-06 0.000 mg/dscm 3.23E-03 1.52E-03 1.29E-03 0.002 mg/dscm@7%O2 3.12E-03 1.46E-03 1.23E-03 0.002



### Compound: Nickel Average RunNumber 1 2 3 Mass_mg 0.01978 0.0035 0.0132 0.012 lb/mmBtuO2 2.70E-06 4.81E-07 1.83E-06 0.000



### Monday, February 07, 2011 Page 9 of 19

### Process Run Data mg/dscm 3.04E-03 5.44E-04 2.08E-03 0.002 mg/dscm@7%O2 2.93E-03 5.21E-04 1.98E-03 0.002



### Compound: Selenium Average RunNumber 1 2 3 Mass_mg 0.1398 0.0927 0.085 0.106 lb/mmBtuO2 1.91E-05 1.27E-05 1.18E-05 0.000 mg/dscm 2.15E-02 1.44E-02 1.34E-02 0.016 mg/dscm@7%O2 2.08E-02 1.38E-02 1.28E-02 0.016



### Location: Stack - OTM - 27 Compound: Filterable PM2.5 Average RunNumber 1 2 3 Mass_mg 3.5 2.4 4 3.300 lb/mmBtuO2 9.07E-04 6.03E-04 1.01E-03 0.001



### Location: Stack - OTM - 28 Compound: Inorganic (Aqueous) Condensible P Average RunNumber 1 2 3 Mass_mg 41.2 15.2 14.7 23.700 lb/mmBtuO2 1.07E-02 3.82E-03 3.71E-03 0.006



### Compound: Organic Condensible Particulate Average RunNumber 1 2 3 Mass_mg 4.9 7 7.2 6.367 lb/mmBtuO2 1.27E-03 1.76E-03 1.82E-03 0.002



### Monday, February 07, 2011 Page 10 of 19

### Process Run Data

APCD Run Data

Process Lab Run Data Run Name Value UOM Comments Target Value
1 Gross Electric output (THC) 709.99 MW 0

1 Gross Electric output (Formaldehyde) 709.99 MW 0

1 Gross Electric output (OTM 27 and 28) 706.97 MW 0

1 Gross Electric Output (Metals and PM) 706.97 MW 0

Monday, February 07, 2011 Page 11 of 19

### Sampling / Stack Data Results Detail

Location Stack - Method 0011 Average Run Number 1 2 3
Test Date 5/6/2010 5/6/2010 5/6/2010 Run Start Time 8:45:00 AM 11:10:00 AM 1:34:00 PM Run Finish Time 10:52:00 AM 1:18:00 PM 3:42:00 PM Net Traversing Points 24 24 23 Net Run Time, minutes 120 120 120 Nozzle Diameter, inches 0.18 0.18 0.18 0.180 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.986 0.986 0.986 0.986 Barometric Pressure, inches of Mercury 29.35 29.35 29.35 29.350 Average Orifice Meter Differential, inches H2O 1.34 1.37 1.33 1.347 Dry Gas Meter Volume Sampled, cubic feet 79.164 79.949 78.521 79.211 Average Dry Gas Meter Temperature, °F 91.25 97.29 99.48 96.007 Dry Gas Meter Volume Sampled, dscf 73.585 73.515 71.912 73.004 Total Moisture Liquid collected, g 212 212.2 204.2 209.467 Volume of Water Vapor, standard cubic feet 9.98 9.99 9.61 9.860 Moisture Content of Stack Gas, % 11.94 11.96 11.79 11.897 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8806 0.8804 0.8821 0.881 Carbon Dioxide, % 13.4 13.4 13.5 13.433 Oxygen, % 6.3 6.3 6.2 6.267 Carbon Monoxide & Nitrogen, % 80.3 80.3 80.3 80.300 Fuel Factor 1.09 1.09 1.09 Dry Molecular Weight, lb/lb-Mole 30.40 30.40 30.41 30.403 Wet Molecular weight, lb/lb-Mole 28.92 28.92 28.95 28.930 Flue Gas Static Pressure, inches of H2O -2.5 -2.5 -2.5 -2.500 Absolute Flue Gas Pressure, inches of Mercury 29.17 29.17 29.17 29.170 Average Stack Gas Temperature, °F 300.71 309.00 312.57 307.427 Average Velocity Head, inches of H2O 1.9127665831 5807 1.950537099

46986 1.901667200

91467 1.922

Average Stack Gas Velocity, feet/second 94.31 95.76 94.72 94.930 Stack Cross-Sectional Area, square feet 490.874 490.874 490.874 490.874 Dry Volumetric Flow Rate, dry scfm 1,655,188.1 1,662,141.0 1,639,652.1 1,652,327.0 67 Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,777,659.6 2,820,365.7 2,789,735.1 2,795,920.1 33 Percent Isokinetic of Sampling Rate, % 102.9 102.4 101.5 102.267 Percent Excess Air, % 42.3 42.3 41.3 41.967 F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000 Round Duct Diameter, inches 300 300 300 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0
Fw
Fc



### Monday, February 07, 2011 Page 12 of 19

### Location Stack - Method 10 Average

Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type
Fw
Fc Cgasw Cgasw Units



### Monday, February 07, 2011 Page 13 of 19

### Location Stack - Method 25A Average

Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type
Fw
Fc Cgasw Cgasw Units



### Monday, February 07, 2011 Page 14 of 19

### Location Stack - Method 29 Average

Run Number
Test Date Run Start Time
Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, %
Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches
Fw
Fc



### Monday, February 07, 2011 Page 15 of 19

### Location Stack - Method 3A CO2 Average

Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type
Fw
Fc Cgasw Cgasw Units



### Monday, February 07, 2011 Page 16 of 19

### Location Stack - Method 3A O2 Average

Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type
Fw
Fc Cgasw Cgasw Units



### Monday, February 07, 2011 Page 17 of 19

### Location Stack - OTM - 27 Average

Run Number
Test Date Run Start Time
Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, %
Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches
Fw
Fc



### Monday, February 07, 2011 Page 18 of 19

### Location Stack - OTM - 28 Average

Run Number
Test Date Run Start Time
Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, %
Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches
Fw
Fc



### Monday, February 07, 2011 Page 19 of 19