# Revised Final Fourth Quarter 2012 - Quarterly Groundwater Monitoring Report Outside Tunnel Wells

Red Hill Bulk Fuel Storage Facility Joint Base Pearl Harbor-Hickam, Oahu, Hawaii

DOH Facility ID: 9-102271 DOH Release ID: 990051, 010011, and 020028

January 2013



## Department of the Navy Naval Facilities Engineering Command, Hawaii 400 Marshall Road JBPHH, HI 96860-3139

Contract Number N 62742-12-D-1853, CTO 0002This Page Intentionally Left Blank.

# Revised Final Fourth Quarter 2012 - Quarterly Groundwater Monitoring Report Outside Tunnel Wells

Red Hill Bulk Fuel Storage Facility Joint Base Pearl Harbor-Hickam, Oahu, Hawaii

DOH Facility ID: 9-102271 DOH Release ID: 990051, 010011, and 020028

January 2013

Prepared for:



## Department of the Navy Naval Facilities Engineering Command, Hawaii 400 Marshall Road JBPHH, HI 96860-3139

Prepared by: 

## Environmental Science International, Inc. 354 Uluniu Street, Suite 304 Kailua, HI 96734

Prepared under:


## Contract Number N 62742-12-D-1853, CTO 0002This Page Intentionally Left Blank.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM,4Q2012 Status Re port Page v January 2013 

### REVISED FINAL FOURTH QUARTER 2012 - QUARTERLY GR OUNDWATER MONITO RING REPORT OUTSIDE TUNNEL WELLS RED HILL BULK FUEL STORAGE FACILITY

Long-Term Groundwater and Soil Vapor Monitoring Red Hill Bulk Fuel Storage Facility Joint-Base Pearl Harbor-Hickam, Oahu, Hawaii



### Prepared for: Department of the Navy Commanding Officer, Naval Facilities Engineering Command, Hawaii 400 Marshall Road JBPHH, HI 96860-3139



### Prepared by: Environmental Science International, Inc. 354 Uluniu Street, Suite 304 Kailua, HI 96734 (808) 261-0740



### Prepared under: Contract Number: N62742-12-D-1853 Contract Task Order: 0002

Approval Signature: Darren Uchima, Navy Technical Representative Date

Approval Signature: 1/17/13 Robert Chong, ESI Project Manager Date

Approval Signature: 1/17/13 Traci Sylva, ESI QA Manager DateContract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM,4Q2012 Status Repo rt Page vi January 2013 This Page Intentionally Left Blank.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM,4Q2012 Status Repo rt Page vii January 2013 TABLE OF CONTENTS

Section Title Page

ES EXECUTIVE SUMMARY ES-1

1.0 INTRODUCTION 1-1 1.1 Site Description 1-1 1.2 Physical Settings 1-2 1.3 Background 1-3

2.0 GROUNDWATER SAMPLING 2-1 2.1 Groundwater Sampling 2-1 2.2 Analytical Results 2-1 2.3 Waste Disposal 2-2

3.0 DATA QUALITY ASSESSMENT 3-1

3.1 Data Validation and Assessment 3-1

3.2 Data Assessment and Usability Conclusions 3-3

4.0 SUMMARY, CONCLUSIONS, AND RECOMMENDATIONS 4-1

5.0 FUTURE WORK 5-1

6.0 REFERENCES 6-1Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM,4Q2012 Status Repo rt Page viii January 2013 LIST OF TABLES

Number Title Page

1.1 Current Status of USTs 1-2 2.1 Analytical Results for Groundwater Sampling (November 7, 2012) 2-3 3.1 Quality Control Results for Groundwater Sampling (November 7, 2012, 2012) 3-5

LIST OF FIGURES

Number Title

1 Site Location 2 Site Layout

APPENDICES

Appendix Title

A Groundwater Sampling Logs
B Field Notes C Laboratory Reports D Waste Disposal ManifestContract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM,4Q2012 Status Repo rt Page ix January 2013 

## ACRONYMS AND ABBREVIATIONS

ACRONYMS/ ABBREVIATIONS DEFINITION/MEANING

% percent COPC Contaminant of Potential Concern DLNR State of Hawaii Department of Land and Natural Resources DOH State of Hawaii Department of Health DON Department of the Navy EAL Environmental Action Level EPA Environmental Protection Agency ESI Environmental Science International F-76 Marine Diesel Fuel ID Identification JBPHH Joint Base Pearl Harbor-Hickam JP-5 Jet Fuel Propellant-5 JP-8 Jet Fuel Propellant-8 LCS Laboratory Control Sample LCSD Laboratory Control Sample Duplicate LOD Limit of Detection LOQ Limit of Quantitation μg/L micrograms per Liter MS Matrix Spike MSD Matrix Spike Duplicate NAVFAC Naval Facilities Engineering Command NAVSUP FLC Naval Supply Systems Command Fleet Logistics Center N.D. Not Detected PAH Polycyclic Aromatic Hydrocarbons PARCCS Precision, Accuracy, Representat iveness, Completeness, Comparability, and Sensitivity pH hydrogen activity QC Quality Control RHSF Red Hill Bulk Fuel Storage Facility RPD Relative Percent Difference SAP Sampling and Analysis Plan TEC The Environmental Company, Inc. TPH-d Total Petroleum Hy drocarbons as diesel TPH-g Total Petroleum Hydrocarbons as gasoline U.S. United States of America UST Underground Storage Tank VOC Volatile Organic Compounds WP Work PlanContract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM,4Q2012 Status Re port Page x January 2013 This Page Intentionally Left Blank.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report ES-1 January 2013

EXECUTIVE SUMMARY

This quarterly monitoring report presents the results of the fourth quarter 2012 groundwater sampling event conducted on November 7, 2012, at the outside tunnel wells of the Red Hill Bulk Fuel Storage Facility [RHSF], Joint Base Pearl Harbor-Hickam [JBPHH], Hawaii. The RHSF is located in Halawa Heights on the Island of Oahu. There are 18 active and 2 inactive underground storage tanks located at the RHSF. The State of Hawaii Department of Health [DOH] Facility Identification [ID] number is 9-102271. The DOH Release ID numbers are 990051, 010011, and

020028.

The groundwater sampling was conducted as part of the long-term groundwater and soil vapor monitoring at the RHSF, under Naval Facilities Engineering Command [NAVFAC] Contract Number N62742-12-D-1853. The sampling was conducted in accordance with the approved Work Plan [WP]/Sampling and Analysis Plan [SAP] pr epared by Environmental Science International [ESI].

On November 7, 2012, Environmental Science International [ESI] personnel collected groundwater samples from two outside tunnel monitoring wells (wells HDMW2253-03 and OWDFMW01). A summary of the analytical results is provided below.

 HDMW2253-03 – Total Petroleum Hydrocarbons as di esel [TPH-d] (25 micrograms per Liter [μg/L]) and Total Petroleum Hydrocarbons as gasoline [TPH-g] (15 μg/L) were detected. None of the chemical constituents analyzed for were detected at concentrations above the DOH Environmental Action Levels [EALs].

 OWDFMW01 – TPH-d (2,500 μg/L), TPH-g (17 μg/L), naphthalene (0.025 μg/L), and benzene (0.38 μg/L) were detected. TPH-d was detected at concentrations above the DOH EALs for both drinking water toxicity and gross contamination.

Since the wells were last sampled (July 2012), with the exception of TPH-d, groundwater
contaminant concentrations remained at low c oncentrations and did not change significantly, or were not detected. TPH-d concentrations increased substantially in well OWDFMW01. This was the highest TPH-d concentration detected since quarterly groundwater monitoring was initiated in 2009. TPH-d concentrations increased from non-detect (less than 80.8 μg/L) during the last round of sampling to 2,500 μg/L during this round of sampling.

Based on the results of the assessment, we recommend continuing the groundwater monitoring program at the RHSF. If TPH-d concentrations in well OWDFMW01 continue to increase, we recommend increasing monitoring frequency to monthly even though well OWDFMW01 is not
included in the RHSF Groundwater Protection Plan.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report ES-2 January 2013 This Page Intentionally Left Blank.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 1-1 January 2013

SECTION 1 – INTRODUCTION

This quarterly monitoring report presents the results of the fourth quarter 2012 groundwater sampling event conducted on November 7, 2012, at the outside tunnel wells of the RHSF, JBPHH, Hawaii. The RHSF is located in Halawa Heights on the Island of Oahu. The purpose of the sampling is to (1) assess the condition of groundwater beneath and in the vicinity of the RHSF with respect to chemical constituents associated with jet fuel propellant and marine diesel fuel, and (2) to ensure the Navy remains in compliance with DOH Underground Storage Tank [UST] release response requirements as described in Hawaii Administrative Rules 11-281 Subchapter 7, Release Response Action (DOH, 2000). The DOH Facility ID number for the RHSF is 9-102271. The DOH Release ID numbers are 990051, 010011, and 020028.

The groundwater sampling was conducted as part of the long-term groundwater and soil vapor monitoring at the RHSF, under NAVFAC Contract Number N62742-12-D-1853. The sampling was conducted in accordance with the appr oved WP/SAP prepared by ESI (ESI, 2012).

1.1 S ITE D ESCRIPTION

The RHSF is located on federal government land (zoned F1- Military and Federal), located in Halawa Heights, approximately 2.5 miles northeast of Pearl Harbor (Figure 1). It is located on a low ridge on the western edge of the Koolau Mountain Range that divides Halawa Valley from Moanalua Valley. The RHSF is bordered on the north by Halawa Correctional Facility and private businesses, on the west by the United Stat es of America [U.S.] Coast Guard reservation, on the south by residential neighborhoods, and on the east by Moanalua Valley. A quarry is located less than a quarter mile away to the northwest. The RHSF occupies 144 acres of land and the majority of the site is at an elevati on of approximately 200 to 500 feet above mean sea
level.

The RHSF contains 18 active and 2 inactive USTs, which are operated by Naval Supply Systems Command Fleet Logistics Center [NAVSU P FLC] Pearl Harbor (formerly Fleet and Industrial Supply Center). Each UST has a capacity of approximately 12.5 million gallons. The RHSF is located approximately 100 feet above the basal aquifer. The USTs contain Jet Fuel Propellant-5 [JP-5], Jet Fuel Propellant-8 [JP-8], and Marine Diesel Fuel [F-76]. The current
status of each of the USTs is summarized in Table 1.1.

Two groundwater monitoring wells (well HDMW2253-03 and OWDFMW01) are located outside of the RHSF tunnel system (Figure 2). Well HDMW2253-03 is located at the Halawa Correctional Facility (outside the RHSF) and well OWDFMW01 is located at the Oily Waste Disposal Facility near Adit 3. Five groundwat er monitoring wells (wells RHMW01, RHMW02, RHMW03, RHMW05, and RHMW2254-01) are located within the RHSF lower access tunnel. (Monitoring data for the five wells located inside the tunnel are included in a separate report.)

Monitoring wells RHMW01, RHMW02, RHMW03, and RHMW05 are located inside the underground tunnels. Monitoring well RHMW2254-01 is located inside the infiltration gallery of the Department of the Navy [DON] Well 2254-01. DON Well 2254-01 is located approximatelyContract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 1-2 January 2013

2,400 feet downgradient of the USTs and provides approximately 24 percent [%] of the potable water to the Pearl Harbor System, which se rves approximately 52,200 military customers. NAVFAC Public Works Department operates th e infiltration gallery and DON Well 2254-01.

TABLE 1.1 Current Status of the USTs Quarterly Groundwater Monitoring Reporting – Outside Tunnel Wells Red Hill Bulk Fuel Storage Facility

Tank Identification Fuel Type Status Capacity F-1 None Inactive 12.5 million gallons F-2 JP-8 Active 12.5 million gallons F-3 JP-8 Active 12.5 million gallons F-4 JP-8 Active 12.5 million gallons F-5 JP-8 Active 12.5 million gallons F-6 JP-8 Active 12.5 million gallons F-7 JP-5 Active 12.5 million gallons F-8 JP-5 Active 12.5 million gallons F-9 JP-5 Active 12.5 million gallons F-10 JP-5 Active 12.5 million gallons F-11 JP-5 Active 12.5 million gallons F-12 JP-5 Active 12.5 million gallons F-13 F-76 Active 12.5 million gallons F-14 F-76 Active 12.5 million gallons F-15 F-76 Active 12.5 million gallons F-16 F-76 Active 12.5 million gallons F-17 JP-5 Active 12.5 million gallons F-18 JP-5 Active 12.5 million gallons F-19 None Inactive 12.5 million gallons F-20 JP-5 Active 12.5 million gallons

F-76 Marine Diesel Fuel
JP-5 Jet Fuel Propellant-5
JP-8 Jet Fuel Propellant-8

1.2 P HYSICAL S ETTINGS

Climatological conditions in the area of the RHS F consist of warm to moderate temperatures and low to moderate rainfall. The RHSF is leeward of the prevailing northeasterly trade winds. The average annual precipitation is approximately 40 inches, which occurs mainly between November and April (State of Hawaii Department of Land and Natural Resources [DLNR], 1986). Annual pan evaporation is approximately 75 inches (DLNR, 1985). Average temperatures range from the low 60’s to high 80’s (degrees Fahrenheit) (Atlas of Hawaii, 1983).

Oahu consists of the eroded remnants of two shield volcanoes, Waianae and Koolau. The RHSF is located on the southwest flank of the Koolau volcanic shield. Lavas erupted during the shield-building phase of the volcano belong to the Koolau Volcanic Series (Stearns and Vaksvik, 1935). Following formation of the Koolau shield, a long period of volcanic quiescence occurred, during which the shield was deeply eroded. Following this erosional period, eruptive activity resumed. Lavas and pyroclastic material erupted during this period belong to the Honolulu
Volcanic Series (Stearns and Vaksvik, 1935).Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 1-3 January 2013

In the immediate area of the RHSF, Koolau Volcanic Series lavas dominate, although there are consolidated and unconsolidated non-calcareous deposits in the vicinity that consist of alluvium generated during erosion of the Koolau volcanic shield. South-southwest of the Site, and in isolated exposures to the west, are pyroclas tic deposits formed during eruptions from three Honolulu Volcanic Series vents, Salt Lake, Aliamanu, and Makalapa (Stearns and Vaksvik, 1935). Based on established geology and records of the drilled wells (Stearns and Vaksvik, 1938), the RHSF is underlain by Koolau Volcanic Series basalts.

The area of the RHSF is classified as Rock Land , where 25 to 90% of the land surface is covered by exposed rock and there are only shallow soils (Foote, et al., 1972).

Groundwater in Hawaii exists in two principal types of aquifers. The first and most important type, in terms of drinking water resources, is the basal aquifer. The basal aquifer exists as a lens of fresh water floating on and displacing seawater within the pore spaces, fractures, and voids of the basalt that forms the underlying mass of each Hawaiian island. In parts of Oahu, groundwater in the basal aquifer is confined by the overlying caprock and is under pressure. Waters that flow freely to the surface from wells that tap the basal aquifer are referred to as
artesian

.

The second type of aquifer is the caprock aquifer, which consists of various kinds of unconfined and semi-confined groundwater. Commonly, the caprock consists of a thick sequence of nearly impermeable clays, coral, and basalt, which s eparates the caprock aquifer from the basal aquifer. The impermeable nature of these materials and the artesian nature of the basal aquifer severely restrict the downward migration of groundwater from the upper caprock aquifer. In the area of the RHSF, there is no discernible caprock.

Shallow groundwater in the area of the RHSF is part of the Waimalu Aquifer System of the Pearl Harbor Aquifer Sector. The aquifer is classified as a basal, unconfined, flank-type; and is currently used as a drinking water source. The aquifer is considered fresh with less than 250 milligrams per liter of chloride and is considered an irreplaceable resource with a high vulnerability to contamination (Mink and Lau, 1990).

The nearest drinking water supply well is the DON Well 2254-01, located in the infiltration gallery within the RHSF. DON Well 2254-01 is located approximately 2,400 feet downgradient of the USTs (Figure 2).

1.3 B ACKGROUND

The RHSF was constructed by the U.S. Government in the early 1940s. Twenty USTs and a series of tunnels were constructed to supply f uel to the Navy. The USTs were constructed of steel and they currently contain JP-5, JP-8, and F-76. Several tanks in the past have stored DON special fuel oil, DON distillate, aviation gasoline, and motor gasoline (Environet, 2010). The fueling system is a self-contained underground unit that was installed into native rock comprised primarily of basalt with some interbedded tuffs and breccias (Environet, 2010). EachContract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 1-4 January 2013

UST measures approximately 245 feet in height and 100 feet in diameter. The upper domes of the tanks lie at a depth varying between 100 feet and 200 feet below ground surface.

In response to increasing concentrations of Contaminant of Potential Concerns [COPCs] in the groundwater monitoring wells within the facility (specifically RHMW02) during the 2008 sampling events, quarterly groundwater monitoring was initiated in 2009 at the outside tunnel wells.

In 2009, groundwater samples were collected from wells RHMW04, OWDFMW01, and HDMW2253-03. Samples were collected in August and October 2009. None of the COPCs were detected at concentrations exceeding the gross contamination or drinking water toxicity
DOH EALs.

In 2010, groundwater samples were collected from wells RHMW04, OWDFMW01, and HDMW2253-03. Samples were collected from well RHMW04 in January and April 2010. Samples were collected from well OWDFMW01 in January, April, and October 2010. Samples were collected from well HDMW2253-03 in January, April, July and October 2010. The COPCs concentrations exceeding DOH EALs are summarized below.

 HDMW2253-03 – TPH-d was detected at a concentration above the gross contamination and drinking water toxicity DOH EAL in January 2010 (The Environmental Company, Inc. [TEC], 2010a).

 OWDFMW01 – TPH-d was detected at a concentration above the gross contamination and drinking water toxicity DOH EALs in January and April 2010 (TEC, 2010a; TEC, 2010b).

In 2011, groundwater samples were collected from wells OWDFMW01 and HDMW2253-03. Samples were collected in January, April, July, and October 2011. None of the COPCs were detected at concentrations exceeding the gross contamination or drinking water toxicity DOH
EALs

In 2012, groundwater samples were collected from wells OWDFMW01 and HDMW2253-03. Samples were collected in January, April, and July 2012. TPH-d was detected at a concentration above the DOH EALs in samples collected from wells HDMW2253-03 and OWDFMW01 (Environet, 2012). The COPCs concentrations exceeding DOH EALs are
summarized below.

 HDMW2253-03 – TPH-d was detected at a concentration above the gross contamination and drinking water toxicity DOH EAL in April 2012.

 OWDFMW01 – TPH-d was detected at a concentration above the gross contamination and drinking water toxicity DOH EAL in April 2012.

1.3.1 Previous Reports

The following groundwater monitoring reports we re previously submitted to the DOH:

1. Groundwater Monitoring Report, August 2009 (submitted September 2009).Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 1-5 January 2013

2. Groundwater Monitoring Report, October 2009 (submitted December 2009).

3. Groundwater Monitoring Report, January, 2010 (submitted April 2010).

4. Groundwater Monitoring Report, April 2010 (submitted May 2010).

5. Groundwater Monitoring Report, July 2010 (submitted August 2010).

6. Groundwater Monitoring Report, October 2010 (submitted December 2010).

7. Groundwater Monitoring Report, January 2011 (submitted March 2011).

8. Groundwater Monitoring Report, April 2011 (submitted June 2011).

9. Groundwater Monitoring Report, July 2011 (submitted September 2011).

10. Groundwater Monitoring Report, October 2011 (submitted December 2011).

11. Groundwater Monitoring Report, January 2012 (submitted March 2012).

12. Groundwater Monitoring Report, April 2012 (submitted July 2012).

13. Groundwater Monitoring Report, July 2012 (submitted August 2012).Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 1-6 January 2013 This Page Intentionally Left Blank.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 2-1 January 2013

SECTION 2 – GROUNDWATER SAMPLING

On November 7, 2012, ESI personnel collected groundwater samples from two monitoring wells (wells OWDFMW01 and HDMW2253-03). The samples were collected in accordance with DOH UST release response requirements and the RHSF Groundwater Protection Plan (TEC, 2008). Generally, the depth to groundwater in the wells is measured using an oil/water interface probe prior to sampling; however, the Solinst 122 oil/water interface probe that was provide as part of the contract was not long enough to measure the depth to groundwater in well OWDFMW01. Thus, the depth to water in well OWDFMW01 was not measured. The DLNR measured the depth to water and depth to bottom of well HDMW2253-03 using their Geotech oil/water interface probe. The measurements are included in the groundwater sampling log. No measurable product or petroleum hydrocarbon odor was observed in either well.

2.1 G ROUNDWATER S AMPLING

Prior to collecting groundwater samples, disposable bailers were used to purge groundwater from the monitoring wells. The wells were purged at a rate of 0.22 and 0.38 liters per minute.

Water quality parameters were monitored on a periodic basis during well purging. The water quality parameters that were measured incl uded hydrogen activity [pH], temperature, conductivity, dissolved oxygen, and oxidation reduction potential. The water quality parameters were evaluated to demonstrate that the natural characteristics of the aquifer formation water were present within the monitoring well before collecting the sample. At least four readings were collected during the purging process. Purging was considered complete when at least three consecutive water quality measurements stabilized within approximately 10%. The readings were recorded on groundwater monitoring logs which are included in Appendix A. The field notes are included in Appendix B.

When the water quality parameters stabilized, groundwater samples were collected from the wells. The disposable bailers were used to collect the groundwater samples from the monitoring wells. For each monitoring well, the groundwater samples were collected no more than two hours after purging was completed to prevent groundwater interaction with the monitoring well casing and atmosphere. Samples collected for dissolved lead were filtered in the field using a peristaltic pump and a 0.45 micron filter.

2.2 A NALYTICAL R ESULTS

The samples were analyzed for TPH-d using U.S. Environmental Protection Agency [EPA] Method 8015M, TPH-g and Volatile Organic Compounds [VOCs] using EPA Method 8260B, Polycyclic Aromatic Hydrocarbons [PAHs] using EPA Method 8270C SIM, and dissolved lead using EPA Method 6020. The analytical results are summarized below and in Table 2.1. A copy of the laboratory report is included in Appendix C.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 2-2 January 2013

 HDMW2253-03 – TPH-d (25 μg/L) and TPH-g (15 μg/L) were detected. None of the chemical constituents analyzed for were detected at concentrations above the gross contamination or drinking water toxicity DOH EALs.

 OWDFMW01 – TPH-d (2,500 μg/L), TPH-g (17 μg/L), naphthalene (0.025 μg/L), and benzene (0.38 μg/L) were detected. TPH-d was detected at concentrations above the DOH EALs for both drinking water toxicity and gross contamination.

2.2.1 Groundwater Contaminant Trends

 HDMW2253-03 – Both TPH-d and TPH-g were detected; however, both were detected at low concentrations. TPH-g had not been detected in previous sampling events. TPH-d concentrations detected during this round of quarterly sampling were consistent with
historical data.

 OWDFMW01 – With the exception of TPH-d, groundwater contaminant concentrations remained at low concentrations and did not change significantly, or were not detected. TPH-d concentrations detected during this round of sampling were the highest concentrations detected since quarterly groundwater monitoring was initiated in 2009. TPH-d concentrations increase from non-detect (less than 80.8 μg/L) during the last round of sampling to 2,500 μg/L during this round of sampling.

2.3 W ASTE D ISPOSAL

The purged groundwater and decontamination water generated during sampling of the wells was stored in a 55-gallon drum along with the purged water and decontamination water from the inside tunnel wells. The drum was stored onsite at Adit 3. On December 10, 2012, the drum of water was picked up by Pacific Commercial Services, LLC and disposed at Unitek Solvent Services, Inc. The waste disposal manifest is included in Appendix D.Contract No. N62742-12-D-1853Contract Task Order 0002Red Hill LTM, 4Q2012 StatusReport 2-3 January 2013TABLE 2.1Analytical Results for Groundwater Sampling (November 7, 2012)Red Hill Bulk Fuel Storage FacilityNovember 2012 Quarterly Status ReportChemicalConstituentOWDFMW01(ES007)OWDFMW01(ES008)(Dup)HDMW2253-03(ES009)LODDOH EALsDrinkingWaterToxicityGrossContaminationTPH-d2,5002,50025 20 190 100TPH-gN.D.17 15 30 100 100Naphthalene0.0350.025N.D. 0.05 17 21Benzene 0.49 0.38 N.D. 0.5 5 170The data are in micrograms per Liter (μg/L).Shaded values exceeded the DOH EALs.DOH EALsDOH Environmental Action Levels for groundwater where groundwater is a current drinking water source andsurface water is greater than 150 meters from the site (DOH, Fall 2011).LOD Limit of DetectionN.D.Not DetectedTPH-d Total Petroleum Hydrocarbons as dieselTPH-gTotal Petroleum Hydrocarbons as gasolineContract No. N62742-12-D-1853Contract Task Order 0002Red Hill LTM, 4Q2012 StatusReport 2-4 January 2013This Page Intentionally Left Blank.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 3-1 January 2013

SECTION 3 – DATA QUALITY ASSESSMENT

A data quality assessment, which consists of a review of the overall groundwater sample collection and analysis process, was performed in order to determine whether the analytical data generated meet the quality objectives for the project. The field Quality Control [QC] program consisted of standardized sample collection and management procedures, and the collection of field duplicate samples, matrix spike samples, and trip blank samples. The laboratory quality assurance program consisted of the use of standard analytical methods and the preparation and analyses of Matrix Spike [MS]/Matrix Spike Duplicate [MSD] samples, surrogate spikes, method blanks, Laboratory Control Samples [LCS] and Laboratory Control Sample Duplicate [LCSD].

3.1 Data Validation and Assessment

The objective of data validation is to provide dat a of known quality for project decisions. Data quality is judged in terms of its Precision, Accuracy, Representativeness, Completeness, Comparability, and Sensitivity [PARCCS]. A number of factors may affect the quality of data, including: sample collection methods, sample analysis methods, and adherence to established procedures for sample collection, preservation, management, shipment, and analysis.

Precision
Precision is defined as the reproducibility of rep licate measurements. Precision is evaluated by Relative Percentage Difference [RPD] of field duplicates and laboratory LCS/LCSD or MS/MSD results. Field duplicate and MS/MSD samples were collected at a rate of approximately 10% of project samples. Field duplicates were sent to the laboratory along with the primary samples.

For this monitoring event, the RPDs for MS/MSD and LCS/LCSD pairs were all within the acceptable range. The RPDs of detected analytes for the primary and field duplicate samples (ES007 and ES008) are provided in Table 3.1. All RPDs for the three analytes detected in both samples were less than 50% (as recommended in the NAVFAC Project Procedures Manual (DON 2007)), although three of the detects (TPH-g, naphthalene, and benzene) were below the Limit of Detection [LOD], and thus qualified as estimated (J flag). The fourth analyte, TPH-d was detected above the DOH EAL, and with excellent precision (RPD = 0%). Therefore the data precision is considered acceptable.

Accuracy
Accuracy is defined as the degree of agreement of a measurement to an accepted reference or true value. Accuracy is evaluated through measurem ent of the percent recovery of an analyte in a reference standard or spiked sample. Accuracy limits for surrogates, laboratory control spike, MS, and MSD samples are established by the indivi dual laboratory. The acceptance criteria for accuracy are dependent on the analytical method and are based on historical laboratory data.

All of the LCS and surrogate spike recoveries for analyzed constituents were within acceptable percent recovery limits. The MS or MSD recoveri es for several VOCs were outside of controlContract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 3-2 January 2013

limits (high recoveries for 1,1-Dichloroethylene, acetone, tetrachloroethylene, and trans-1,2- dichloroethylene, and low recoveries for 1,1,2-Trichloroethane and for 1,1,2,2- Tetrachloroethane). All other MS and MSD recoveries were within acceptable recovery limits, therefore, the data accuracy for this monitoring event is considered acceptable.

Representativeness
Representativeness is the degree that data accurately and precisely represents a characteristic of a population, parameter variations at a sampling point, or an environmental condition. Representativeness was achieved by conducting sampling in compliance with the sample collection procedures described in the Work Plan specifically written for this project (ESI, 2012).

Representativeness is also evaluated through the compliance with the sample holding time, sample preservation, and the analysis of blank samples, including method blank and trip blank samples. The sample holding time was exceeded for TPH-g and VOCs for both samples due to laboratory error, and therefore these results are qualified as estimated because a low bias is possible. The sample holding time for TPH-d, PAHs, and lead and sample preservation complied with the EPA criteria. For this sampling event, one trip blank was collected to determine blank contribution during sample transport for TPH-g and VOCs. There was no detection of VOCs in the trip blank. TPH-g was detected in the method blank below the LOD. Therefore, the groundwater sample data are considered representative of the groundwater quality on site.

Completeness
Completeness is defined as the overall percentage of valid analytical results (including estimated results) compared to the total number of analytical results reported by the analytical laboratory. No data were rejected for this project, and therefore the completeness goal for this project (90%), was successfully met. Successful completion of data acquisition can only be accomplished if both the field and laboratory portions of the project are performed according to the procedures described in the Work Plan (ESI, 2012).

Comparability
Comparability expresses the confidence with which one data set can be compared to another data set. Comparability can be related to accuracy and precision because these quantities are measures of data reliability. Data, with acce ptable precision and accuracy, are considered comparable if collection techniques, analytical procedures, methods and reporting are equivalent. For this monitoring event, the samples were collected using approaches consistent with those in the previous events, and the same analytical methods/procedures were used to measure the concentration of COPCs. Therefore, the results are considered comparable within this data set and with the data collected from previous sampling events.

Sensitivity
The Limits of Quantitation [LOQs] are established by the laboratory based on the LODs or instrument detection limits, historical data, and EPA limits established for the methods. The LOQs for samples may require adjustment due to matrix interference or if high levels of targetContract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 3-3 January 2013

analytes necessitate dilution before analysis. Matrix interference and sample dilutions have the effect of increasing the LOQs. Laboratory LODs and LOQs for several analytes differed from the LODs and LOQs in the Work Plan [WP]/Sam pling And Analysis Plan [SAP] because the laboratory updates them quarterly. LODs and LOQs for several analytes were greater than the EALs (as stated in the WP/SAP) and therefore it is not possible to determine whether the analytes are present at the EAL. As suggeste d by the DOH Technical Guidance Manual, the project action level will be the LOD for these analytes.

3.2 Data Assessment and Usability Conclusions

The PARCCS criteria were evaluated, and with a few exceptions, all criteria were met. These exceptions include the exceedances of recovery criteria for MS/MSDs for several VOCs and analysis of VOCs outside of the recommended hold time. Since the surrogate recoveries and the recoveries of the VOCs in the LCS/LCSD are all within recovery criteria, the MS/MSD exceendaces are not considered to affect the usability of the data, but may indicate some matrix heterogeneity or inconsistencies due to the missed hold time. There is the possibility of a low bias in VOC results due to hold time exceedance, and therefore, this data should be considered estimated, and carefully examined in relation to data in previous and future GW monitoring events. Since the data are consistent with data from previous events, it appears that the effect of this QC exceedance is not substantial, and the data is usable. The data assessment concludes that all data generated during this event are usable for the intended use for project
decisions.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 3-4 January 2013 This Page Intentionally Left Blank.Contract No. N62742-12-D-1853Contract Task Order 0002Red Hill LTM, 4Q2012 Status Report3-5January 2013TABLE 3.1Quality Control Results for Groundwater Sampling (November 7, 2012)Red Hill Bulk Fuel Storage FacilityNovember 2012 Quarterly Status ReportMethodChemicalConstituentDOH EALsOWDFM01 (ES007)OWDFMW01 (ES008)RPDDuplicate(%)ES TripDrinkingWaterToxicityGrossContaminationResultsQLOQLODDLResultsQLOQLODDLResultsQLOQLODDLEPA 8015B TPH-d 190 1002,500HD 50 20 152,500HD 50 20 15 0 - - - - -EPA 8260B TPH-g 100 100 N.D. BU,B 50 30 13 17 BU,U 50 30 13 0 17 U 200 100 44EPA 8270C SIM (PAHs) Naphthalene 17 21 0.035 J 2 0.05 0.23 0.025 J 2 0.05 0.23 33.33 - - - - -EPA 8260B (VOCs) Benzene 5 170 0.49 BU,J 1 0.5 0.14 0.38 BU,J 1 0.5 0.14 25.29 n.d. BU,U 1 0.5 0.14EPA 6020 Lead 15 50,000 N.D. U 1 0.2 0.0898 N.D. U 1 0.2 0.0898 0 - - - - -The data are in micrograms per Liter (μg/L).Shaded values exceeded the DOH EALs.- Not AnalyzedB Analyte was present in the associated method blank.BU Sample analyzed after holding time expired.DL Detection Limit.DOH EALs DOH Environmental Action Levels for groundwater where groundwater is a current drinking water source and surface wateris greater than 150 meters from the site (DOH, Fall 2011).HD The chromatic pattern was inconsistent withthe profile of the reference fuel standard.J Analyte was detected at a concentration below theLOQ and above the DL. Reported value is estimated.LOD Limit of Detection.LOQLimit of Quantitation.N.D. Not DetectedQ Qualifier.TPH-gTotal Petroleum Hydrocarbons as gasolineTPH-dTotal Petroleum Hydrocarbons as dieselU Undetected at DL and is reported as less than the LOD.Contract No. N62742-12-D-1853Contract Task Order 0002Red Hill LTM, 4Q2012 Status Report3-6January 2013This Page Intentionally Left Blank.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 4-1 January 2013

SECTION 4 – SUMMARY, CONCLUSIONS, AND RECOMMENDATIONS

This quarterly monitoring report presents the results of groundwater sampling conducted on November 7, 2012, at the RHSF, JBPHH, Hawaii. The RHSF is located in Halawa Heights on the Island of Oahu. The DOH Facility ID number for the RHSF is 9-102271. The DOH Release ID numbers are 990051, 010011, and 020028.

The groundwater sampling was conducted as part of the long-term groundwater and soil vapor monitoring at the RHSF, under NAVFAC Contract Number N62742-12-D-1853. The sampling
was conducted in accordance with the approved WP/SAP prepared by ESI.

On November 7, 2012, ESI personnel collected groundwater samples from two monitoring wells (wells HDMW2253-03 and OWDFMW01). A summary of the analytical results is provided
below.

 HDMW2253-03 – TPH-d (25 μg/L) and TPH-g (15 μg/L) were detected. None of the chemical constituents analyzed for were detected at concentrations above the DOH EALs.

 OWDFMW01 – TPH-d (2,500 μg/L), TPH-g (17 μg/L), naphthalene (0.025 μg/L), and benzene (0.38 μg/L) were detected. TPH-d was detected at concentrations above the DOH EALs for both drinking water toxicity and gross contamination.

Groundwater Contaminant Trends

 HDMW2253-03 – Both TPH-d and TPH-g were detected; however, both were detected at low concentrations. TPH-g had not been detected in previous sampling events. TPH-d concentrations detected during this round of quarterly sampling were consistent with
historical data.

 OWDFMW01 – With the exception of TPH-d, groundwater contaminant concentrations remained at low concentrations and did not change significantly, or were not detected. TPH-d concentrations detected during this round of sampling were the highest concentrations detected since quarterly groundwater monitoring was initiated in 2009. TPH-d concentrations increase from non-detect (less than 80.8 μg/L) during the last round of sampling to 2,500 μg/L during this round of sampling.

Conclusions and Recommendations Since the wells were last sampled (July 2012), with the exception of TPH-d, groundwater
contaminant concentrations in wells HDMW2253-03 and OWDFMW01 remained at low concentrations and did not change significantly, or were not detected. TPH-d concentrations increased substantially in well OWDFMW01.

Based on the results of the assessment, we recommend continuing the groundwater monitoring program at the RHSF. If TPH-d concentrations in well OWDFMW01 continue to increase, we recommend increasing monitoring frequency to monthly even though well OWDFMW01 is not
included in the RHSF Groundwater Protection Plan.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 4-2 January 2013

A copy of this report will be submitted to the DOH and a copy will be kept on file at NAVFAC.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 5-1 January 2013

SECTION 5 – FUTURE WORK

G ROUNDWATER S AMPLING Future work includes the first quarter 2013 groundwater monitoring in January 2013. It is anticipated that the quarterly groundwater monitoring status report will be submitted in February

2013.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 5-2 January 2013 This Page Intentionally Left Blank.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 6-1 January 2013

SECTION 6 – REFERENCES

Atlas of Hawaii, 1983, Department of Geography, University of Hawaii Press.

DLNR, 1985, Pan Evaporation: State of Hawai’i 1894-1983: Report R74, Division of Water and Land Development, August 1995.

DLNR, 1986, Rainfall Atlas of Hawaii: Report R76, Division of Water and Land Development,
June 1986.

DOH, 2000, Hawaii Department of Health, Technical Guidance Manual for Underground Storage Tank Closure and Release Response, March 2000.

DOH, 2011, Screening for Environmental Hazards at Sites with Contaminated Soil and Groundwater, Hawai'i Department of Health, Hazard Evaluation and Emergency Response,
December 2011.

DON, 2007, Project Procedures Manual, U.S. Na vy Installation Restoration Program, NAVFAC Pacific, Prepared for Pacific Division, Naval Facilities Engineering Command (NAVFAC Pacific), February 2007.

Environet, 2010, Work Plan, Long-Term Monitoring, Red Hill Bulk Fuel Storage Facility, Pearl Harbor, Oahu, Hawaii, September 2010.

Environet, 2012, Quarterly Groundwater Monitoring Report-Outside (Non-Tunnel Wells), Red Hill Bulk Fuel Storage Facility, Pearl Harbor, Oahu, Hawaii, July 2012.

ESI, 2012, Work Plan/Sampling and Analysis Plan, Red Hill Bulk Fuel Storage Facility, Pearl Harbor, Oahu, Hawaii, October 2012.

Foote et al., 1972, Soil Survey of the Islands of Kauai, Oahu, Maui, Molokai, and Lanai, State of
Hawaii.

Mink, J. F. and Lau, L. S., 1990, Aquifer Identif ication and Classification for Oahu: Groundwater Protection Strategy for Hawaii: Water Resources Research Center Technical Report No. 179, February 1990.

Stearns, H. T. and Vaksvik, K. N., 1935, Geology and Groundwater Resources of the Island of Oahu, Hawaii: Hawaii Div. Hydrogr. Bull.

Stearns, H. T. and Vaksvik, K. N., 1938, Records of the Drilled Wells on the Island of Oahu, Hawaii: Hawaii Div. Hydrogr. Bull. 4, 213 p.

TEC, 2008, Final Groundwater Protection Plan, Red Hill Fuel Storage Facility, Prepared for Navy Region Hawaii, Pearl Harbor, Hawaii, January 2008.Contract No. N62742-12-D-1853 Contract Task Order 0002

Red Hill LTM, 4Q2012 Status Report 6-2 January 2013

TEC, 2010a, Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells, Prepared for Navy Region Hawaii, Pearl Harbor, Hawaii, April 2010.

TEC, 2010b, Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells, Prepared for Navy Region Hawaii, Pearl Harbor, Hawaii, May 2010.

# FIGURESThis Page Intentionally Left Blank.KAENAPOINTKAHUKUMAKAHAMAILINANAKULIWAIANAEBARBERSPOINTEWABEACHHONOLULUINTERNATIONALAIRPORTWAIKIKIDIAMONDHICKAMAFBKAPOLEIEWAMOKULEIAHALEIWAWAIMEAPOINTLAIEPUNALUUKAAAWAWAIAHOLEKANEOHE BAYKANEOHEMOKAPUKAILUAWAIMANALOMAKAPUUPOINTHAWAIIKAIKAHALAHONOLULUWAHIAWASCHOFIELDBARRACKSPEARL CITY8393080399807808361637872618383676637809393075099H3H1H1H1H2(RESIDENTIAL HOUSING)HALAWACORRECTIONALFACILITYNAVY FIRING RANGERED HILL BULK FUELSTORAGE FACILITYHALAWA SHAFTBOARD OF WATER SUPPLYPUMP STATION (2354-01)GRAPHIC SCALE0900900Scale in FeetThe accuracy of this document is limited to the qualityand scale of the source information. This document isnot a legal representation of an engineered survey.NOTESSOURCESPearl Harbor Base MapNavy GIS filesPROJECTLOCATIONFIGURE 1SITE LOCATIONGROUNDWATER MONITORINGRED HILL BULK FUEL STORAGE FACILITYNAVAL SUPPLY SYSTEM COMMAND (NAVSUP)FLEET LOGISTICS CENTERJBPHH, OAHU, HAWAIIThis Page Intentionally Left Blank.RHMW05RHMW04HDMW2253-03SVMP04SVMP06SVMP12SVMP14SVMP16SVMP18SVMP20SVMP17SVMP15SVMP11SVMP09SVMP07SVMP05SVMP03RHMW03(RESIDENTIAL HOUSING)OWDFMW01RED HILL BULK FUELSTORAGE FACILITYSVMP13SVMP08HALAWACORRECTIONALFACILITYNAVY FIRING RANGEHALAWA SHAFTBOARD OF WATER SUPPLYPUMP STATION (2354-01)RHMW2254-01U.S. Navy Well 2254-01RHMW01SVMP02RHMW02SVMP10GRAPHIC SCALE01,2001,200Scale in FeetThe accuracy of this document is limited to the qualityand scale of the source information. This document isnot a legal representation of an engineered survey.NOTESRED HILL BULK FUEL STORAGE FACILITYHALAWA CORRECTIONAL FACILITYHALAWA STREAMBUILDINGROADABOVEGROUND STORAGE TANKWATER TANKSOIL VAPOR MONITORING POINTGROUNDWATER MONITORING WELLBOARD OF WATER SUPPLY PUMPSTATIONLEGENDSOURCESPearl Harbor Base MapNavy GIS filesFIGURE 2SITE LAYOUTGROUNDWATER MONITORINGRED HILL BULK FUEL STORAGE FACILITYNAVAL SUPPLY SYSTEM COMMAND (NAVSUP)FLEET LOGISTICS CENTERJBPHH, OAHU, HAWAIIThis Page Intentionally Left Blank.

# APPENDIX A

Groundwater Sampling LogsThis Page Intentionally Left Blank.

## Groundwater Sampling Log

Well ID: Location: Project No.:

Initial Water Level: Time:

Total Depth of Well: Personnel Involved:

Length of Saturated Zone: Weather Conditions:

Volume of Water to be Removed: Method of Removal:

Water Level After Purging: Pumping Rate:

Well Purge Data:

Sample Withdrawal Method: Appearance of Sample:

Color: Turbidity:

Sediment:

Other:

Laboratory Analysis Parameters and Preservatives:

Number and Types of Sample Containers: Sample Identification Numbers:

Decontamination Procedures:

Notes: Sampled by: Sampled Delivered to: Transporters:
Date: Time: Red Hill Bulk Fuel Storage Facility 112066

- Date: 11/7/2012 800 OWDFMW01

-

Time Volume Removed pH Conductivity (mS/cm) DO (mg/l) Justin Lam, Branden Ibara

Windy, Partly Cloudy

Disposable Bailer

Temperature Salinity Redox (ORP) (mV)

Capacity of Casing (Gallons/Linear Feet)
2"-0.16 • 4"-0.65 • 8"-2.61 • 10"-4.08 • 12"-5.87 12.50

12.67

12.75 0.35 L/min

- - -

810

820 12.30

12.52 3.235

3.262

824

829

832 0

2

4

6

8 3.289

3.323 5.25

5.60

5.05

5.00

5.03 3.285

24.19 24.13 23.97 24.19 24.81 1.68

1.70

1.72

1.72

1.74 -164.3

-185.4

-185.4

-186.4

-187.6

TPH-g, TPH-d - 8015; VOCs - 8260; PAHs - 8270C

lead - 6020

ES007 [0830], ES008 (Dup) [0900], ES008 MS/MSD [0900] Clear

Low Slight

16 - VOAs, 6 - 1L amber jar, 4 - 500ml amber jar, 4 - 500ml HDPE bottle Disposable Bailer

Triple Rinsed

Justin Lam, Branden Ibara Calscience Environmental Lab FedEx

re

## Groundwater Sampling Log

Well ID: Location: Project No.:

Initial Water Level: Time:

Total Depth of Well: Personnel Involved:

Length of Saturated Zone: Weather Conditions:

Volume of Water to be Removed: Method of Removal:

Water Level After Purging: Pumping Rate:

Well Purge Data:

Sample Withdrawal Method: Appearance of Sample:

Color: Turbidity:

Sediment:

Other:

Laboratory Analysis Parameters and Preservatives:

Number and Types of Sample Containers: Sample Identification Numbers:

Decontamination Procedures:

Notes: Sampled by: Sampled Delivered to: Transporters:
Date: Time: Red Hill Bulk Fuel Storage Facility 112066

208.2 ft Date: 11/7/2012 1115 HDMW2253-03

1575 ft Justin Lam, Branden Ibara

- Sunny

- Disposable Bailer

- 0.22 L/min

Time Volume Removed pH Conductivity (mS/cm) DO (mg/l) Temperature Salinity Redox (ORP) (mV)

1118 0 9.25 0.492 1.50 22.99 0.24 -217.5

1123 1 8.96 0.477 1.43 22.59 0.23 -195.7

1127 2 8.95 0.475 1.53 22.45 0.23 -179.0

1132 3 8.93 0.474 1.33 22.4 0.23 -178.7

1136 4 8.93 0.474 1.35 22.44 0.23 -173.0

Clear

Low Slight

TPH-g, TPH-d, - 8015; VOCs - 8260; PAHs - 8270C Disposable Bailer

lead - 6020

ES009 [1200]
Triple Rinsed

Justin Lam, Branden Ibara 6 - VOAs, 2 - 1L amber jar, 1 - 500ml amber jar, 1 - 500ml HDPE bottle

Calscience Environmental Lab FedEx

Capacity of Casing (Gallons/Linear Feet)
2"-0.16 • 4"-0.65 • 8"-2.61 • 10"-4.08 • 12"-5.87

re

# APPENDIX B

Field NotesThis Page Intentionally Left Blank.

# APPENDIX C

Laboratory ReportsThis Page Intentionally Left Blank.

### Analytical Report For
Client: Environmental Science International, Inc. Client Project Name: Red Hill LTM 112066

Attention: Robert Chong

354 Uluniu Street, Suite 304 Kailua, HI 96734-2500 

# WORK ORDER NUMBER: 12-11-0711

Richard Villafania Project Manager 11/19/2012 

### Page 1 of 34

# Contents

Client Project Name: Red Hill LTM 112066

Work Order Number: 12-11-0711



### 1 Client Sample Data

. . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 3 1.1 EPA 6020 ICP/MS Metals (Aqueous)

. . . . . . . . . . . . . . . . . . . . . . . . 3 1.2 EPA 8015B (M) TPH Diesel (Aqueous)

. . . . . . . . . . . . . . . . . . . . . . . 4 1.3 EPA 8270C SIM PAHs (Aqueous)

. . . . . . . . . . . . . . . . . . . . . . . . . . 5 1.4 GC/MS GRO/EPA 8260B Volatile Organics (Aqueous)

. . . . . . . . . . . . 9

2 12-11-0711 Case Narrative

. . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 19

3 Quality Control Sample Data

. . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 20 3.1 MS/MSD and/or Duplicate

. . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 20
3.2 LCS/LCSD

. . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 26

4 Glossary of Terms and Qualifiers

. . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 31

5 Chain of Custody/Sample Receipt Form

. . . . . . . . . . . . . . . . . . . . . . . . . 32 Page 2 of 34Return to Contents 

### Page 3 of 34Return to Contents 

### Page 4 of 34Return to Contents 

### Page 5 of 34Return to Contents 

### Page 6 of 34Return to Contents 

### Page 7 of 34Return to Contents 

### Page 8 of 34Return to Contents 

### Page 9 of 34Return to Contents 

### Page 10 of 34Return to Contents 

### Page 11 of 34Return to Contents 

### Page 12 of 34Return to Contents 

### Page 13 of 34Return to Contents 

### Page 14 of 34Return to Contents 

### Page 15 of 34Return to Contents 

### Page 16 of 34Return to Contents 

### Page 17 of 34Return to Contents 

### Page 18 of 34Return to Contents 

### Page 19 of 34Return to Contents 

### Page 20 of 34Return to Contents 

### Page 21 of 34Return to Contents 

### Page 22 of 34Return to Contents 

### Page 23 of 34Return to Contents 

### Page 24 of 34Return to Contents 

### Page 25 of 34Return to Contents 

### Page 26 of 34Return to Contents 

### Page 27 of 34Return to Contents 

### Page 28 of 34Return to Contents 

### Page 29 of 34Return to Contents 

### Page 30 of 34Return to Contents 

### Page 31 of 34Return to Contents 

### Page 32 of 34Return to Contents 

### Page 33 of 34Return to Contents 

### Page 34 of 34

# APPENDIX D

Waste Disposal ManifestThis Page Intentionally Left Blank.This Page Intentionally Left Blank.