page 1

Permit No

. N98765 

## PERMIT TO CONSTRUCT/OPERATE A/N 

### 577000

This initial permit must be renewed ANNUALL Y unless the equipment is moved, or changes ownership. If the billing for annual renewal fee (Rule 301.f) is not received by the expiration date, contact the District.



## SAMPLE Legal Owner ID 084742 or Operator: SOUTH COAST AIR QUALITY MANAGEMENT DISTRICT

21865 COPLEY DRIVE

DIAMOND B A R , CA 9 1 765

Equipment Location: 21865 COPLEY DRIVE

, DIAMOND BAR, CA 91765

Equipment Description:

Fuel Storage and Dispensing Facility Consisting of:

1) 1 2

- G asoline B alance N ozzles D ispensing 3 6 P roducts E quipped with B alance P hase II E nhanced V apor
R ecovery (EVR) S ystem with a [VST M embrane , V eeder

- R oot V apor F ilter , F ranklin F ueling S ystems H ealy

C lean A ir S eparator , H irt VCS 100 , VST G reen M achine ] P rocessor I ncluding [ V eeder

- R oot , I ncon (ONLY WITH VST/CAS)] I n

- S tation D iagnostics (ISD) S ystem with S oftware V ersion N umber 1.05 /TS

- VRM Version

1.3.0 (VR

- 20 4

- R )

.

2) 3

- Gasoline Underground Storage Tanks, Each 20,000 Gallon Capacity, Equipped with Phase I Vapor Recovery System OPW (VR

- 102

- D/ O ), 3 Methanol Compatible.

2) 1

- Gasoline Underground Storage Tank, 20,000 Gallon Capacity, Equipped with Phase I Vapor Recovery Sy stem Phil

- Tite (VR

- 101

- D/N), 1 Methanol Compatible

.

3) 1

- D ual C ompartment U nderground G asoline /D iesel S torage T ank , 22,000 G allon C apacity , 1 M ethanol

C ompatible , C onsisting O f :

A) O ne 12,000 G allon G asoline C ompartment , E quipped with P hase I V apor R e covery S ystem OPW (VR

102

- O ).

B) O ne 10,000 G allon D iesel C ompartment , N ot E quipped with P hase I V apor R ecovery S ystem

.

4) Liquid Condensate Trap with an Automatic Liquid Evacuating System

.

Conditions:

SECTION I: GENERAL CONDITIONS

1. Operation of this equipment shall be in compliance with all data and specifications submitted with the application under which this permit was issued, unless otherwise noted below.

2. This equipment sh all be properly maintained and kept in good operating condition at all times.

SECTION II: PHASE I VAPOR RE C O V ERY SYSTEM AND TESTING REQUIREMENTSpage Permit No

. N98765 

## PERMIT TO CONSTRUCT/OPERATE A/N 

### 577000

CONTINUATION OF PERMIT TO CONSTRUCT/OPERATE



## SAMPLE 2

3. Except for diesel transfers, Phase I vapor recovery systems shall be in full operation whenever gasoline fuel is being transferred into storage tanks.

4

. A static torque test of rotatable phase I adaptors shall be conducted to quantify the amount of static torque required to start the rotation of the rotatable of the rotatable phase I adaptors. The test sha ll be conducted in accordance with the test procedure method outlined in TP

- 201.1B (O ctober 8, 2003) as a performance test and as

a reverification test. R esults shall be submitted to the SC AQMD, O ffice of E ngineering and Compliance within
seventy

- two (72) hours of test

.

5

. D epending on the system configuration

, either a leak rate test of drop tube / drain valve assembly shall be conducted to quantify the pressure integrity of both the drop tube and drain valve seal or a leak rate test of drop

tube overfill prevention device and drain valve shall be conducted to quantify the pressure integrity of the drop tube overfill prevention device and the pressure integrity of the spill container drain valve . E ither test shall be conducted in accordance with test proce dure method TP

- 201.1C (O ctober 8, 2003) or TP

- 201.1D (O ctober 8, 2003), respectively

. R esults shall be submitted to the SC AQMD, O ffice of E ngineering and Compliance within

seventy

- two (72) hours of test

.

6. A leak rate and cracking pressure test of press ure / vacuum relief vent valves shall be conducted within ten ( 1 0) days after the start of operation of the phase I EVR equipment and at least once every three (3) years thereafter to determine the pressure and vacuum at which the pressure/vacuum vent valve actuates

, and to determine the volumetric leak rate at a given pressure . T he test shall be conducted in accordance with the test procedure

method TP

- 201.1E (O ctober 8, 2003). R esults shall be submitted to the SC AQMD, O ffice of E ngineering and Compliance within seventy

- two (72) hours of test

. T his test result shall be kept on site for three (3) years and

made available to D istrict representatives upon request

.

SECTION III: PHASE II VAPOR RECOVERY SYSTEM AND TESTING REQUIREMENTS

7

. Except for diesel tra nsfers, Phase II vapor recovery systems shall be in full operation whenever fuel is being transferred into motor vehicles, as defined in Rule 461.

8. A static pressure integrity test shall be conducted to demonstrate that the storage tanks, the remote and /or nozzle vapor recovery check valves, associated vapor return piping and fittings are free from vapor leaks. The test shall be conducted in accordance with CARB test procedure method TP

- 201.3 (March 17, 1999), as a performance

test and as a reverificati on test. R esults shall be submitted to the SC AQMD, O ffice of E ngineering and Compliance within seventy

- two (72) hours of test

.

9. The static pressure leak decay test TP

- 201.3, shall be conducted in accordance with the most recent version of

Exhibit 4 of CARB Executive Order VR

- 204. Verification of completing each step as outlined shall be documented by submitted a copy of Exhibit 4 to the SCAQMD, O ffice of E ngineering and Compliance within

seventy

- two (72) hours of test

.

10. T he P hase II vapor recovery system shall be installed

, operated

, and maintained such that the maximum allowable pressure through the system including nozzle

, vapor hose

, swivels

, and underground piping does not exceed the dynamic back pressures described by the C alifornia A ir R esourc es B oard E xecutive O rder by which the system was certified :

NITROGEN FLOWRATES DYNAMIC BACK PRESSURE (CFH) (I nches of W ater )

60 0.35page Permit No

. N98765 

## PERMIT TO CONSTRUCT/OPERATE A/N 

### 577000

CONTINUATION OF PERMIT TO CONSTRUCT/OPERATE



## SAMPLE 3

80 0.62

Dynamic back pressure tests shall be conducted to d etermine the Phase II system vapor recovery back pressures. as a performance test to determine the phase II system vapor recovery back pressures. The tests shall be conducted in accordance with CARB test procedure TP

- 201.4, Methodology 1 (July 3, 2002); as a performance

test and as a reverification test

. Furthermore, CARB test procedure TP

- 201.4, Methodology 6 (July 3, 2002); shall be conducted within ten (10) days from start of operation as a performance test only. A copy of the TP

201.4, Methodology 6 test result shall remain permanently on site. R esults shall be submitted to the SC AQMD,

O ffice of E ngineering and Compliance within seventy

- two (72) hours of test s

.

11

. T he dynamic back pressure tests TP

- 201.4, shall be conducted in accordance with th e latest version of E xhibit 6

of C ARB E xecutive O rder VR

- 204. V erification of completing each step as outlined shall be documented by submitting a copy of E xhibit 6 to the SC AQMD, O ffice of E ngineering and C ompliance within seventy

- two (72)

hours of test

.

12

. A liquid removal test shall be conducted to quantify the removal rate of liquid from the vapor passage of a P hase

II balance system hose equipped with a liquid removal device . T he test shall be conducted in accordance with

the latest version of E xh ibit 5 of CARB E xecutive O rder VR

- 204

, as a performance test and reverification test

. R esults shall be submitted to the SC AQMD, O ffice of E ngineering and Compliance within seventy

- two (72)

hours of test

.

13. A nozzle bag test shall be conducted on the balance Phase II EVR nozzles to verify the integrity of the vapor valve. The test shall be conducted on any newly installed or replaced balance P hase II EVR nozzles and in

accordance with the latest version of E xhibit 7 OF CARB E xecutive O rder VR

- 204. R e sults shall be submitted

to the SC AQMD, O ffice of E ngineering and Compliance within seventy

- two (72) hours of test

.

14

. IF A VST ECS MEMBRANE PROCESSOR IS INSTALLED, A hydrocarbon sensor verification test shall be conducted to determine the accuracy of th e VST hydrocarbon non

- dispersive infrared sensor (HC SENSOR) using known hydrocarbon concentrations ( propane ) calibration gases at gasoline dispensing facilities . T he test

shall be conducted in accordance with the latest version of E xhibit 8 of CARB E xecu tive O rder VR

- 204, as a performance test and as a reverification test

. R esults shall be submitted to the SC AQMD, O ffice of E ngineering and Compliance within seventy

- two (72) hours of test

.

15

. IF A VST ECS MEMBRANE PROCESSOR IS INSTALLED, A determination of processor activation pressure test shall be conducted to determine compliance with the VST processor activation pressure requirement

. T he

test shall be conducted in accordance with the latest version of E xhibit 9 of CARB E xecutive O rder VR

- 204, as a

p erformance test and as a reverification test

. R esults shall be submitted to the SC AQMD, O ffice of E ngineering and Compliance within seventy

- two (72) hours of test

.

16

. A vapor pressure sensor verification test shall be conducted to determine the pressure management control vapor pressure sensor is operating in accordance with the pressure sensor requirements

. T he test shall be conducted in

accordance with the latest version of E xhibit 10 of CARB E xecutive O rder VR

- 204, as a performance test and as

a reve rification test

. R esults shall be submitted to the SC AQMD, O ffice of E ngineering and Compliance within

seventy

- two (72) hours of test

.

17. IF A VEEDER

- ROOT VAPOR POLISHER IS INSTALLED, A V eeder

- R oot vapor polisher operability test

shall be conducted to verify the pressure integrity of the vapor polisher

, confirm that the operating pressure is within certification parameters at a known flow rate

, and verify the readings of the various thermometer elements and atmospheric pressure sensor

. T he test shall b e conducted in accordance with the latest version of E xhibit 11page Permit No

. N98765 

## PERMIT TO CONSTRUCT/OPERATE A/N 

### 577000

CONTINUATION OF PERMIT TO CONSTRUCT/OPERATE



## SAMPLE 4

of CARB E xecutive O rder VR

- 204, as a performance test and as a reverification test

. R esults shall be submitted

to the SC AQMD, O ffice of E ngineering and Compliance within seventy

- two (72) hour s of test

.

1 8

. IF A VEEDER

- ROOT VAPOR POLISHER IS INSTALLED, A V eeder

- Root vapor polisher hydrocarbon emissions verification test shall be conducted to verify the proper performance of the V eeder

- R oot vapor polisher

. T he test shall be conducted in accord ance with the latest version of E xhibit 12 of CARB E xecutive

O rder VR

- 204, as a performance test and as a reverification test

. R esults shall be submitted to the SC AQMD,

O ffice of E ngineering and Compliance within seventy

- two (72) hours of test

.

19

. I f th e security seal tag on the vapor polisher is broken or missing

, the owner/operator shall perform both a

V eeder

- R oot vapor polisher operability test (E xhibit 11), and a V eeder

- R oot vapor polisher hydrocarbon

emissions verification test (E xhibit 12) within s even (7) days of discovery

, or when it should be reasonably known that such seal is missing or broken . W ithin seven (7) days of a report of a missing or broken security seal
tag

, a new security seal tag shall be applied to the vapor polisher only by a man ufacturer representative and only immediately after passing the above required tests . A new security seal tag shall not be placed and the vapor polisher shall be replaced with a new one if the vapor polisher failed any such tests

.

2 0

. I f the vapor proces sor unit is not accessible for inspection and performing tests purposes from ground level

, the owner/operator shall provide safe access

, which is on

- site and immediately available upon request

, to the vapor processor unit . T he access shall be constructed in accordance with the general industry safety orders of the State

of C alifornia or in compliance with standards specified by the D ivision of O ccupational S afety and H ealth of the

California D epartment of I ndustrial R elations ( ie . CAL/OSHA).

2 1

. IF A HIRT VCS 100 PROCESSOR IS INSTALLED, A H irt VCS 100 P rocessor with indicator panel operability test shall be conducted to verify the operational status of the H irt VCS 100 processor and indicator panel

. T he

test shall be conducted in accordance with the lates t version of E xhibit 13 of CARB E xecutive O rder VR

- 204, as a performance test and as a reverification test

. R esults shall be submitted to the SC AQMD, O ffice of

E ngineering and Compliance within seventy

- two (72) hours of test

.

2 2

. IF A FRANKLIN FUELING SY STEMS HEALY CLEAN AIR SEPARATOR IS INSTALLED, A F ranklin

F ueling S ystems H ealy C lean A ir S eparator static pressure performance test shall be conducted to quantify the vapor tightness of the H ealy C lean A ir S eparator pressure management system

. T he test sh all be conducted in

accordance with the latest version of E xhibit 14 of CARB E xecutive O rder VR

- 204, as a performance test and as

a reverification test

. R esults shall be submitted to the SC AQMD, O ffice of E ngineering and Compliance within

seventy

- two (72) hours of test

.

22. IF A VST GREEN MACHINE IS INSTALLED, A VST G reen M achine annual compliance test consisting of

the GM bag test and continuous monitoring test shall be conducted . T he GM bag test will determine the concentration of hydrocarbons being em itted from the processor and the G reen M achine's capability to control underground storage tank pressure . T he continuous monitoring test will assure that the G reen M achine's continuous monitoring function is working properly

. T he test shall be conducted in accordance with the latest

version of E xhibit 15 of CARB E xecutive O rder VR

- 204, as a performance test and as a reverification test

. R esults shall be submitted to the SC AQMD, O ffice of E ngineering and Compliance within seventy

- two (72)

hours of test

.

23. A liquid condensate trap compliance test shall be conducted to verify the automatic evacuation of the liquid condensate trap, the liquid sensor alarm, and the visual and audible alarms. T he test shall be conducted as a performance test and reverificat ion test, and in accordance with the latest version of E xhibit 16 of CARBpage Permit No

. N98765 

## PERMIT TO CONSTRUCT/OPERATE A/N 

### 577000

CONTINUATION OF PERMIT TO CONSTRUCT/OPERATE



## SAMPLE 5

E xecutive O rder VR

- 204 . R esults shall be submitted to the SC AQMD, O ffice of E ngineering and Compliance within seventy

- two (72) hours of test

.

24

. Access to the condensate trap sha ll be provided for inspection purposes.

25

. An alarm system for liquid accumulation shall be installed and properly maintained for the condensate trap and liquid evacuating system. The alarm system shall be tested prior to start of operation and periodic ally as part of the operation and maintenance manual.

26. In the event of an alarm, no gasoline shall be dispensed at this facility until the condensate trap has been properly evacuated. Furthermore, records shall be kept on all dates of alarms and maint enance requirements.

27

. The owner or operator shall include as part of the operation and maintenance manual, periodic testing and maintenance procedures that demonstrates on

- going compliance. The testing and maintenance procedures shall

include but is n ot limited to the complete shutdown of all turbines, and the operation of the self

- evacuating sumps in case of an alarm.

28

. Only self

- evacuating sumps shall be used in conjunction with the liquid condensate trap.

SECTION IV: IN

- STATION DIAGNOSTICS SYST EM AND TESTING REQUIREMENTS

29

. A n ISD vapor flow meter operability test shall be conducted in accordance with the latest version of either

E xhibit 17 for the V eeder

- R oot ISD system or E xhibit 19 for the I ncon VR M ISD system of CARB E xecutive

O rder VR

- 20 4 to verify the equipment ’ s operability for vapor containment monitoring and vapor collection monitoring . T he test shall be conducted as a performance test and reverification test. F urthermore

, the ISD operability test shall be conducted immediately whene ver a vapor pressure sensor or a vapor flow meter is replaced

. R esults shall be submitted to the SC AQMD, O ffice of E ngineering and Compliance within seventy

two (72) hours of test

.

3 0

. W ithin two (2) hours of detecting the first ISD warning alarm by the ISD system

, the facility attendant shall notify the responsible company official or their designee and request immediate service to correct the problem.

A ll information relating to the alarm event and reporting shall be immediately recorded on an SC AQMD

a pproved form and shall be made available to the D istrict representative upon request . O nly persons authorized by the applicable C ARB certification E xecutive O rders shall be allowed to make vapor recovery or ISD system repairs

.

3 1

. I f THE ISD SYSTEM IS A VEEDER

- ROOT SYSTEM AND a second ISD warning alarm occurs indicating that the same problem still exists or if a failure alarm occurs where gasoline dispensing is terminated

, the ISD system may be reset to allow for vehicle fueling to resume only if :

A) T h e fueling point ( s ) associated with the problem that triggered the failure alarm is isolated and not operated until the required repairs have been completed ; or

B) A n order for abatement or other administrative relief has been issued by the SC AQMD H earing B oard allowing gasoline dispensing to continue ; orpage Permit No

. N98765 

## PERMIT TO CONSTRUCT/OPERATE A/N 

### 577000

CONTINUATION OF PERMIT TO CONSTRUCT/OPERATE



## SAMPLE 6

C) A ll required repairs to correct the problem that triggered the second warning or failure alarm have been completed

, and the necessary applicable tests or procedures have been performed . A listing of the required tests and or procedures can be found in C ARB'S E xecutive O rder VR

- 204 installation

, operation

, and maintenance manual

, section 12 (V eeder

- R oot : ISD installation manual ), subsection 5 ( operation ), table 3 (ISD alarm summary ), and tables 4 and 5 ( other alarms ).

A t a minimum

, all information relating to the alarm event

, course of action taken

, repairs made

, and tests or procedures performed shall be immediately recorded on an SC AQMD approved form and shall be made

available to the D istrict rep resentative upon request

.

3 2

. T he clear test after repair ( reset ) function for the V eeder

- R oot ISD system shall only be utilized once after the

first ISD warning alarm or if the owner/operator has completed either condition 31A, 31B, OR 31C above

.

33

. IF AN INCON ISD SYSTEM IS INSTALLED, A n I ncon vapor pressure sensor verification test shall be

conducted to determine if the I ncon ISD system vapor pressure sensor is operating in accordance with the vapor pressure sensor requirements

. T he test shall be con ducted in accordance with the latest version of E xhibit 20 of

CARB E xecutive O rder VR

- 204, as a performance test and as a reverification test

. R esults shall be submitted to

the SC AQMD, O ffice of E ngineering and Compliance within seventy

- two (72) hours of test

.

3 4

. I f THE ISD SYSTEM IS AN INCON SYSTEM and a second ISD warning alarm occurs indicating that the same problem still exists or if a failure alarm occurs where gasoline dispensing is terminated

, the ISD system may be

reset to allow for vehicle fueli ng to resume only if :

A) T he fueling point ( s ) associated with the problem that triggered the failure alarm is isolated and not operated until the required repairs have been completed ; or

B) A n order for abatement or other administrative relief has bee n issued by the SC AQMD H earing B oard allowing gasoline dispensing to continue ; or

C) A ll required repairs to correct the problem that triggered the second warning or failure alarm have been completed

, and the necessary applicable tests or procedures have been performed :

WARNING OR ALARM DESCRIPTION APPLICABLE TEST(S) OR PROCEDURE(S)

D aily or weekly vapor collection TP

- 201.4 and TP

- 201.3

W eekly or monthly ullage pressure TP

- 201.3

W eekly ullage pressure leak TP

- 201.3

A ll other warnings or alarms R efer to A ppendix A of I ncon vapor recovery monitoring installation

, operation, and

maintenance manual.

A t a minimum

, all information relating to the alarm event

, course of action taken

, repairs made

, and tests or procedures performed sh all be immediately recorded on an SC AQMD approved form and shall be made

available to the D istrict representative upon request

.

3 5

. O nly a certified I ncon technician may manually clear any vapor collection or pressure related failure alarms, or if

the own er/operator has completed either condition 34A, 34B, or 34C above

.page Permit No

. N98765 

## PERMIT TO CONSTRUCT/OPERATE A/N 

### 577000

CONTINUATION OF PERMIT TO CONSTRUCT/OPERATE



## SAMPLE 7

3 6

. There shall be no gasoline dispensing if the ISD system is shut off, tampered with, disconnected, or otherwise

disabled

.

SECTION V: GENERAL REQUIREMENTS

3 7

. All Phase I and Phase II vapor recovery equipment at this facility shall be installed, operated and maintained to meet all California Air Resources Board certification requirements.

3 8

. A ll permit conditions applicable to the equipment described in the previous Permit to Operate N24498 shall remain in effect until the new or modified equipment is constructed and operated as described in this new permit

. T his Permit to C onstruct/Operate shall become invalid if the modification as described in the equipment description has not bee n completed within one year from the issue date

. I f the modification has not been completed within one year from the issue date of the permit, a written request shall be submitted to the

SC AQMD (A ttention : R andy M atsuyama ) to reinstate the previously ina ctivated permit to operate . A new application shall be filed if there are plans to continue with the modification. F urthermore, this condition does not allow any time extensions to any modifications required by the C alifornia A ir R esources B oard or

SC AQM D.

3 9

. The District at its discretion may wish to witness the installation and/or performance testing of the new vapor recovery equipment. At least seventy

- two (72) hours prior to the installation of the equipment and any of the mentioned testing requi rements in this permit, the applicant shall notify the SCAQMD by methods specified at the time by the E xecutive O fficer. Such notification shall include the name of the owner or operator, the name of the contractor, the location of the facility, and the s cheduled start and completion dates of the tests to be performed.

40

. N ew equipment installations and subsequent service and repairs for any certified component for which this permit was issued, shall only be performed by a current and certified person wh o has successfully completed the manufacturer's training course and appropriate International Code Council (ICC) certification

. C ompletion of any SC AQMD training course does not constitute as a substitute for this requirement. P roof of successful complet ion of any manufacturer training course shall be with the manufacturer

.

41

. At least seventy

- two (72) hours prior to back

- filling any underground storage tank or piping, the SCAQMD shall be notified electronically or other means as specified by the Execut ive Officer. Such notification shall include the name of the owner or operator; the name of the contractors; the location of the facility; and the scheduled start and completion dates of the back

- filling procedure. The back

- filling procedure shall not co mmence until inspected by a District representative.

42

. Unless SCAQMD Rule 461 requires a more frequent testing or inspection schedule, the owner/operator shall be responsible to perform the scheduled weekly, quarterly, and annual inspections as outlined in the CARB approved Installation, Operation, and Maintenance manual for both the phase I and phase II EVR system, as well as all the required vapor recovery system tests as per the current and appropriate CARB Executive Order.

4 3

. T he SC AQMD shall be no tified electronically or other means as specified by the Executive Officer at least

seventy

- two (72) hours prior to any of the above mentioned testing requirements. S uch notification shall include the name of the owner or operator, the name of the contrac tor, the location of the facil it y, and the scheduled start and completion dates of the tests to be performed.page Permit No

. N98765 

## PERMIT TO CONSTRUCT/OPERATE A/N 

### 577000

CONTINUATION OF PERMIT TO CONSTRUCT/OPERATE



## SAMPLE 8

44. A copy of the pass/fail test results shall be sent electronically or other means as specified by the Executive Officer within seventy

- two (72 ) hours after each test is conducted. Furthermore, the final test results demonstrating compliance shall be submitted electronically or other means as specified by the Executive Officer within fourteen (14) calendar days from the date when all tests were passed. The test report shall include at a minimum all the required records of all tests performed, test data, current SCAQMD facility ID number of the location being tested, the equipment permit to operate or application number, the SCAQMD ID number of t he company performing the tests, a statement whether the system or component tested meets the required standards, and the name, SCAQMD tester ID number and signature of the person responsible for conducting the tests.

4 5

. The testing for the above mention ed tests shall be conducted in accordance with the most recent Rule 461 amendment or CARB Executive Order requirements, whichever is more stringent.

4 6

. All records and test results that are required to be maintained by Rule 461 shall be kept on site for four (4) years and made available to District representatives upon request.

SECTION VI: GASOLINE THROUGHPUT REQUIREMENTS

4 7

. The maximum quantity of gasoline dispensed from the gasoline storage tank at this facility shall not exceed 20,000 gallons in a ny one calendar month nor 240,000 gallons in any one calendar year.

4 8

. Records of monthly annual fuel dispensed shall be prepared, shall be retained on site for two years, and shall be made available to District representatives upon request.

49. The own er/operator shall submit the facility’s monthly gasoline throughput data for the previous calendar year to the Executive Officer on or before March 1 following each calendar year.

NOTICE

In accordance with Rule 206, this permit to operate or copy sha ll be posted on or within 8 meters of the equipment.

This permit does not authorize the emission of air contaminants in excess of those allowed by Division 26 of the Health and Safety Code of the State Of California or the rules of the Air Quality Managem ent District. This permit cannot be considered as permission to violate existing laws, ordinances, regulations or statutes of other government agencies.

E xecutive O fficer

By Dorris M. Bailey/jm04

0 8 / 29 /20 1 5