Instructions for Completing the Process Data Template

This template is to be used to record the 30 daily averages of specific process data required by the ICR. The ERT d

have the capability to store these daily averages. This spreadsheet included 4 separate surrogate worksheets, in 

boiler tested is tested for all surrogates at 4 different dates. This spreadsheet is intended to be used for one boi

facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet.

yellow are required (if applicable to your boilers' operation). You do not need to populate cells shaded in gray, a

automatically populated from the Boiler Information worksheet. Please Do Not modify the structure of this spr

by adding or subtracting rows, columns, cells. Please name each resulting spreadsheet with the following nami

convention: [FacilityID]_Unit_[BoilerID]_Processdata.xls (example: 8100_Unit_2_Processdata.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information workshee

Process Data Worksheets

Please use one process data worksheet for each HAP surrogate even is simultaneous testing of different HAP sur

was done. 
ta Template

s data required by the ICR. The ERT does not 

4 separate surrogate worksheets, in case the 

t is intended to be used for one boiler of one 

es of this spreadsheet. Fields shaded in 

d to populate cells shaded in gray, as they are 

Not modify the structure of this spreadsheet 

preadsheet with the following naming 

nit_2_Processdata.xls).

on the Boiler Information worksheet. 

taneous testing of different HAP surrogates 
EIA Facility Code Facility Name Boiler ID

55749 Hardin Generator Project PC1
EIA Facility Code Facility Name Boiler ID

55749 Hardin Generator Project PC1

Daily Average Process Data for a 30 Day Period Including the Testing Date

Date Coal Firing Rate Coal Firing Rate (units) Synfuel Firing Rate

Day 1 6/29/2010 66 ton/hr

Day 2 6/30/2010 69.1 ton/hr

Day 3 7/1/2010 64.9 ton/hr

Day 4 7/2/2010 68.2 ton/hr

Day 5 7/3/2010 71.1 ton/hr

Day 6 7/4/2010 66.9 ton/hr

Day 7 7/5/2010 65.1 ton/hr

Day 8 7/6/2010 68.5 ton/hr

Day 9 7/7/2010 74.2 ton/hr

Day 10 7/8/2010 77.7 ton/hr

Day 11 7/9/2010 77.4 ton/hr

Day 12 7/10/2010 60.7 ton/hr

Day 13 7/11/2010 75.4 ton/hr

Day 14 7/12/2010 76.3 ton/hr

Day 15 7/13/2010 78.6 ton/hr

Day 16 7/14/2010 78.5 ton/hr

Day 17 7/15/2010 80.4 ton/hr

Day 18 7/16/2010 78.1 ton/hr

Day 19 7/17/2010 78.3 ton/hr

Day 20 7/18/2010 79.8 ton/hr

Day 21 7/19/2010 77.4 ton/hr

Day 22 7/20/2010 75.5 ton/hr

Day 23 7/21/2010 75.9 ton/hr

Day 24 7/22/2010 77 ton/hr

Day 25 7/23/2010 77.2 ton/hr

Day 26 7/24/2010 74.8 ton/hr

Day 27 7/25/2010 77.6 ton/hr

Day 28 7/26/2010 77.8 ton/hr

Day 29 7/27/2010 75.6 ton/hr

Day 30 7/28/2010 75.9 ton/hr
he Testing Date

Synfuel Firing Rate (units) Pet Coke Firing Rate Pet Coke Firing Rate (units) Coal Gas Firing Rate
Coal Gas Firing Rate (units) Fuel oil Firing Rate Fuel oil Firing Rate (units)
Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr)

1063.7

1083.9

1052.7

1120.8

1112.5

1029.2

1053.7

1129.3

1145.3

1248.6

1239.3

797.8

1180.1

1258

1256.2

1261.2

1270.8

1259.9

1253.1

1270.4

1270

1270.6

1243.2

1284

1282.3

1216.7

1268.8

1270.8

1256.5

1255.6
Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe)

90.6 102

93.3 106

92.8 105

93.6 106

92.4 104

84.2 95

86.8 99

93.6 106

92.1 107

104.9 118

104.7 118

43.1 73

99.1 112

103.3 116

105.1 118

97.9 118

106.3 119

104.8 118

104.9 118

102.3 120

106.7 120

106.8 120

104.1 117

106.6 120

106.6 120

103.8 114

103.9 120

106.5 120

105.0 118

105.3 119
Control Device Operating Parameters, As Appicable

Flue Gas Flow Rate (dscfm) Pressure Drop across FGD (in H2O)

240648.1

252293.4

244597.4

253595.7

251917.9

242268.2

242771

255860.3

258547.7

280928.7

278845.9

218296.1

269332.8

276408.3

274958.5

274671.3

279150.1

281350.8

278611.4

280673.7

277001.1

277434

276517.9

283588.8

281110.8

273646.1

282232.2

281693.3

280419.2

279197.8
FGD Scrubber Liquor Flow Rate (gals/min) Sorbent Type Sorbent Injection Rate (lb/hr)

20.1 PAC 25.79

23.4 PAC 25.95

25.1 PAC 28.45

21.2 PAC 15.29

21 PAC 15.37

22.1 PAC 20.58

22.1 PAC 27.75

24.4 PAC 27.33

22.1 PAC 43.75

24.6 PAC 58.33

25.3 PAC 63.2

19.8 PAC 20.71

28 PAC 61.29

26.6 PAC 98.93

21.6 PAC 38.5

20.8 PAC 33.21

20.9 PAC 62.41

34.1 PAC 58.13

26.9 PAC 64.83

23.6 PAC 69.58

23.2 PAC 39.91

24.3 PAC 37.37

23.8 PAC 32.54

27.9 PAC 38.29

26.5 PAC 36

21.4 PAC 41.71

26.4 PAC 42.12

32.4 PAC 41.91

31.6 PAC 42.21

28.9 PAC 45.66
Other Boiler or Control Device Operating Parameters (e.g., Boiler O2) 

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

225.2

219.6

212

215.2

217

209.4

209.7

211

208.8

210

207.7

224.3

210.9

208.5

207.5

205.8

206.2

206.5

211.7

211.2

209.6

207.9

208.5

207.3

210.9

220.5

212.3

206.3

207.6

210.9
Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%)

3.2 11.2 17

3.2 10.9 17

3.3 10.9 17

3 11.2 17

3.2 11.2 17

3.8 10.7 17

3.4 11 17

3.1 11.2 17

3.1 11.2 17

2.9 11.3 17

2.8 11.3 17

7.4 7.7 17

3 11.1 17

2.7 11.5 17

2.7 11.6 17

2.6 11.7 17

2.6 11.6 17

2.7 11.4 17

2.8 11.4 17

2.8 11.5 17

2.5 11.7 17

2.5 11.7 17

2.7 11.4 17

2.6 11.5 17

2.6 11.6 17

3.2 11.2 17

2.7 11.4 17

2.6 11.5 17

2.7 11.4 17

2.6 11.4 17
EIA Facility Code Facility Name Boiler ID

55749 Hardin Generator Project PC1

Daily Average Process Data for a 30 Day Period Including the Testing Date

Date Coal Firing Rate Coal Firing Rate (units) Synfuel Firing Rate

Day 1 6/29/2010 66 ton/hr

Day 2 6/30/2010 69.1 ton/hr

Day 3 7/1/2010 64.9 ton/hr

Day 4 7/2/2010 68.2 ton/hr

Day 5 7/3/2010 71.1 ton/hr

Day 6 7/4/2010 66.9 ton/hr

Day 7 7/5/2010 65.1 ton/hr

Day 8 7/6/2010 68.5 ton/hr

Day 9 7/7/2010 74.2 ton/hr

Day 10 7/8/2010 77.7 ton/hr

Day 11 7/9/2010 77.4 ton/hr

Day 12 7/10/2010 60.7 ton/hr

Day 13 7/11/2010 75.4 ton/hr

Day 14 7/12/2010 76.3 ton/hr

Day 15 7/13/2010 78.6 ton/hr

Day 16 7/14/2010 78.5 ton/hr

Day 17 7/15/2010 80.4 ton/hr

Day 18 7/16/2010 78.1 ton/hr

Day 19 7/17/2010 78.3 ton/hr

Day 20 7/18/2010 79.8 ton/hr

Day 21 7/19/2010 77.4 ton/hr

Day 22 7/20/2010 75.5 ton/hr

Day 23 7/21/2010 75.9 ton/hr

Day 24 7/22/2010 77 ton/hr

Day 25 7/23/2010 77.2 ton/hr

Day 26 7/24/2010 74.8 ton/hr

Day 27 7/25/2010 77.6 ton/hr

Day 28 7/26/2010 77.8 ton/hr

Day 29 7/27/2010 75.6 ton/hr

Day 30 7/28/2010 75.9 ton/hr
e Testing Date

Synfuel Firing Rate (units) Pet Coke Firing Rate Pet Coke Firing Rate (units) Coal Gas Firing Rate
Coal Gas Firing Rate (units) Fuel oil Firing Rate Fuel oil Firing Rate (units)
Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr)

1063.7

1083.9

1052.7

1120.8

1112.5

1029.2

1053.7

1129.3

1145.3

1248.6

1239.3

797.8

1180.1

1258

1256.2

1261.2

1270.8

1259.9

1253.1

1270.4

1270

1270.6

1243.2

1284

1282.3

1216.7

1268.8

1270.8

1256.5

1255.6
Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe)

90.6 102

93.3 106

92.8 105

93.6 106

92.4 104

84.2 95

86.8 99

93.6 106

92.1 107

104.9 118

104.7 118

43.1 73

99.1 112

103.3 116

105.1 118

97.9 118

106.3 119

104.8 118

104.9 118

102.3 120

106.7 120

106.8 120

104.1 117

106.6 120

106.6 120

103.8 114

103.9 120

106.5 120

105.0 118

105.3 119
Control Device Operating Parameters, As Appicable

Flue Gas Flow Rate (dscfm) Pressure Drop across FGD (in H2O)

240648.1

252293.4

244597.4

253595.7

251917.9

242268.2

242771

255860.3

258547.7

280928.7

278845.9

218296.1

269332.8

276408.3

274958.5

274671.3

279150.1

281350.8

278611.4

280673.7

277001.1

277434

276517.9

283588.8

281110.8

273646.1

282232.2

281693.3

280419.2

279197.8
FGD Scrubber Liquor Flow Rate (gals/min) Sorbent Type Sorbent Injection Rate (lb/hr)

20.1 PAC 25.79

23.4 PAC 25.95

25.1 PAC 28.45

21.2 PAC 15.29

21 PAC 15.37

22.1 PAC 20.58

22.1 PAC 27.75

24.4 PAC 27.33

22.1 PAC 43.75

24.6 PAC 58.33

25.3 PAC 63.2

19.8 PAC 20.71

28 PAC 61.29

26.6 PAC 98.93

21.6 PAC 38.5

20.8 PAC 33.21

20.9 PAC 62.41

34.1 PAC 58.13

26.9 PAC 64.83

23.6 PAC 69.58

23.2 PAC 39.91

24.3 PAC 37.37

23.8 PAC 32.54

27.9 PAC 38.29

26.5 PAC 36

21.4 PAC 41.71

26.4 PAC 42.12

32.4 PAC 41.91

31.6 PAC 42.21

28.9 PAC 45.66
Other Boiler or Control Device Operating Parameters (e.g., Boiler O2) 

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

225.2

219.6

212

215.2

217

209.4

209.7

211

208.8

210

207.7

224.3

210.9

208.5

207.5

205.8

206.2

206.5

211.7

211.2

209.6

207.9

208.5

207.3

210.9

220.5

212.3

206.3

207.6

210.9
Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%)

3.2 11.2

3.2 10.9

3.3 10.9

3 11.2

3.2 11.2

3.8 10.7

3.4 11

3.1 11.2

3.1 11.2

2.9 11.3

2.8 11.3

7.4 7.7

3 11.1

2.7 11.5

2.7 11.6

2.6 11.7

2.6 11.6

2.7 11.4

2.8 11.4

2.8 11.5

2.5 11.7

2.5 11.7

2.7 11.4

2.6 11.5

2.6 11.6

3.2 11.2

2.7 11.4

2.6 11.5

2.7 11.4

2.6 11.4
Flue Gas Moisture Content (%)

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17

17
EIA Facility Code Facility Name Boiler ID

55749 Hardin Generator Project PC1

Daily Average Process Data for a 30 Day Period Including the Testing Date

Date Coal Firing Rate Coal Firing Rate (units) Synfuel Firing Rate

Day 1 6/29/2010 66 ton/hr

Day 2 6/30/2010 69.1 ton/hr

Day 3 7/1/2010 64.9 ton/hr

Day 4 7/2/2010 68.2 ton/hr

Day 5 7/3/2010 71.1 ton/hr

Day 6 7/4/2010 66.9 ton/hr

Day 7 7/5/2010 65.1 ton/hr

Day 8 7/6/2010 68.5 ton/hr

Day 9 7/7/2010 74.2 ton/hr

Day 10 7/8/2010 77.7 ton/hr

Day 11 7/9/2010 77.4 ton/hr

Day 12 7/10/2010 60.7 ton/hr

Day 13 7/11/2010 75.4 ton/hr

Day 14 7/12/2010 76.3 ton/hr

Day 15 7/13/2010 78.6 ton/hr

Day 16 7/14/2010 78.5 ton/hr

Day 17 7/15/2010 80.4 ton/hr

Day 18 7/16/2010 78.1 ton/hr

Day 19 7/17/2010 78.3 ton/hr

Day 20 7/18/2010 79.8 ton/hr

Day 21 7/19/2010 77.4 ton/hr

Day 22 7/20/2010 75.5 ton/hr

Day 23 7/21/2010 75.9 ton/hr

Day 24 7/22/2010 77 ton/hr

Day 25 7/23/2010 77.2 ton/hr

Day 26 7/24/2010 74.8 ton/hr

Day 27 7/25/2010 77.6 ton/hr

Day 28 7/26/2010 77.8 ton/hr

Day 29 7/27/2010 75.6 ton/hr

Day 30 7/28/2010 75.9 ton/hr
he Testing Date

Synfuel Firing Rate (units) Pet Coke Firing Rate Pet Coke Firing Rate (units) Coal Gas Firing Rate
Coal Gas Firing Rate (units) Fuel oil Firing Rate Fuel oil Firing Rate (units)
Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr)

1063.7

1083.9

1052.7

1120.8

1112.5

1029.2

1053.7

1129.3

1145.3

1248.6

1239.3

797.8

1180.1

1258

1256.2

1261.2

1270.8

1259.9

1253.1

1270.4

1270

1270.6

1243.2

1284

1282.3

1216.7

1268.8

1270.8

1256.5

1255.6
Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe)

90.6 102

93.3 106

92.8 105

93.6 106

92.4 104

84.2 95

86.8 99

93.6 106

92.1 107

104.9 118

104.7 118

43.1 73

99.1 112

103.3 116

105.1 118

97.9 118

106.3 119

104.8 118

104.9 118

102.3 120

106.7 120

106.8 120

104.1 117

106.6 120

106.6 120

103.8 114

103.9 120

106.5 120

105.0 118

105.3 119
Control Device Operating Parameters, As Appicable

Flue Gas Flow Rate (dscfm) Pressure Drop across FGD (in H2O)

240648.1

252293.4

244597.4

253595.7

251917.9

242268.2

242771

255860.3

258547.7

280928.7

278845.9

218296.1

269332.8

276408.3

274958.5

274671.3

279150.1

281350.8

278611.4

280673.7

277001.1

277434

276517.9

283588.8

281110.8

273646.1

282232.2

281693.3

280419.2

279197.8
FGD Scrubber Liquor Flow Rate (gals/min) Sorbent Type Sorbent Injection Rate (lb/hr)

20.1 PAC 25.79

23.4 PAC 25.95

25.1 PAC 28.45

21.2 PAC 15.29

21 PAC 15.37

22.1 PAC 20.58

22.1 PAC 27.75

24.4 PAC 27.33

22.1 PAC 43.75

24.6 PAC 58.33

25.3 PAC 63.2

19.8 PAC 20.71

28 PAC 61.29

26.6 PAC 98.93

21.6 PAC 38.5

20.8 PAC 33.21

20.9 PAC 62.41

34.1 PAC 58.13

26.9 PAC 64.83

23.6 PAC 69.58

23.2 PAC 39.91

24.3 PAC 37.37

23.8 PAC 32.54

27.9 PAC 38.29

26.5 PAC 36

21.4 PAC 41.71

26.4 PAC 42.12

32.4 PAC 41.91

31.6 PAC 42.21

28.9 PAC 45.66
Other Boiler or Control Device Operating Parameters (e.g., Boiler O2) 

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

225.2

219.6

212

215.2

217

209.4

209.7

211

208.8

210

207.7

224.3

210.9

208.5

207.5

205.8

206.2

206.5

211.7

211.2

209.6

207.9

208.5

207.3

210.9

220.5

212.3

206.3

207.6

210.9
Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%)

3.2 11.2 17

3.2 10.9 17

3.3 10.9 17

3 11.2 17

3.2 11.2 17

3.8 10.7 17

3.4 11 17

3.1 11.2 17

3.1 11.2 17

2.9 11.3 17

2.8 11.3 17

7.4 7.7 17

3 11.1 17

2.7 11.5 17

2.7 11.6 17

2.6 11.7 17

2.6 11.6 17

2.7 11.4 17

2.8 11.4 17

2.8 11.5 17

2.5 11.7 17

2.5 11.7 17

2.7 11.4 17

2.6 11.5 17

2.6 11.6 17

3.2 11.2 17

2.7 11.4 17

2.6 11.5 17

2.7 11.4 17

2.6 11.4 17
EIA Facility Code Facility Name Boiler ID

55749 Hardin Generator Project PC1

Daily Average Process Data for a 30 Day Period Including the Testing Date

Date Coal Firing Rate Coal Firing Rate (units) Synfuel Firing Rate

Day 1 6/29/2010 66 ton/hr

Day 2 6/30/2010 69.1 ton/hr

Day 3 7/1/2010 64.9 ton/hr

Day 4 7/2/2010 68.2 ton/hr

Day 5 7/3/2010 71.1 ton/hr

Day 6 7/4/2010 66.9 ton/hr

Day 7 7/5/2010 65.1 ton/hr

Day 8 7/6/2010 68.5 ton/hr

Day 9 7/7/2010 74.2 ton/hr

Day 10 7/8/2010 77.7 ton/hr

Day 11 7/9/2010 77.4 ton/hr

Day 12 7/10/2010 60.7 ton/hr

Day 13 7/11/2010 75.4 ton/hr

Day 14 7/12/2010 76.3 ton/hr

Day 15 7/13/2010 78.6 ton/hr

Day 16 7/14/2010 78.5 ton/hr

Day 17 7/15/2010 80.4 ton/hr

Day 18 7/16/2010 78.1 ton/hr

Day 19 7/17/2010 78.3 ton/hr

Day 20 7/18/2010 79.8 ton/hr

Day 21 7/19/2010 77.4 ton/hr

Day 22 7/20/2010 75.5 ton/hr

Day 23 7/21/2010 75.9 ton/hr

Day 24 7/22/2010 77 ton/hr

Day 25 7/23/2010 77.2 ton/hr

Day 26 7/24/2010 74.8 ton/hr

Day 27 7/25/2010 77.6 ton/hr

Day 28 7/26/2010 77.8 ton/hr

Day 29 7/27/2010 75.6 ton/hr

Day 30 7/28/2010 75.9 ton/hr
he Testing Date

Synfuel Firing Rate (units) Pet Coke Firing Rate Pet Coke Firing Rate (units) Coal Gas Firing Rate
Coal Gas Firing Rate (units) Fuel oil Firing Rate Fuel oil Firing Rate (units)
Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr)

1063.7

1083.9

1052.7

1120.8

1112.5

1029.2

1053.7

1129.3

1145.3

1248.6

1239.3

797.8

1180.1

1258

1256.2

1261.2

1270.8

1259.9

1253.1

1270.4

1270

1270.6

1243.2

1284

1282.3

1216.7

1268.8

1270.8

1256.5

1255.6
Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe)

90.6 102

93.3 106

92.8 105

93.6 106

92.4 104

84.2 95

86.8 99

93.6 106

92.1 107

104.9 118

104.7 118

43.1 73

99.1 112

103.3 116

105.1 118

97.9 118

106.3 119

104.8 118

104.9 118

102.3 120

106.7 120

106.8 120

104.1 117

106.6 120

106.6 120

103.8 114

103.9 120

106.5 120

105.0 118

105.3 119
Control Device Operating Parameters, As Appicable

Flue Gas Flow Rate (dscfm) Pressure Drop across FGD (in H2O)

240648.1

252293.4

244597.4

253595.7

251917.9

242268.2

242771

255860.3

258547.7

280928.7

278845.9

218296.1

269332.8

276408.3

274958.5

274671.3

279150.1

281350.8

278611.4

280673.7

277001.1

277434

276517.9

283588.8

281110.8

273646.1

282232.2

281693.3

280419.2

279197.8
FGD Scrubber Liquor Flow Rate (gals/min) Sorbent Type Sorbent Injection Rate (lb/hr)

20.1 PAC 25.79

23.4 PAC 25.95

25.1 PAC 28.45

21.2 PAC 15.29

21 PAC 15.37

22.1 PAC 20.58

22.1 PAC 27.75

24.4 PAC 27.33

22.1 PAC 43.75

24.6 PAC 58.33

25.3 PAC 63.2

19.8 PAC 20.71

28 PAC 61.29

26.6 PAC 98.93

21.6 PAC 38.5

20.8 PAC 33.21

20.9 PAC 62.41

34.1 PAC 58.13

26.9 PAC 64.83

23.6 PAC 69.58

23.2 PAC 39.91

24.3 PAC 37.37

23.8 PAC 32.54

27.9 PAC 38.29

26.5 PAC 36

21.4 PAC 41.71

26.4 PAC 42.12

32.4 PAC 41.91

31.6 PAC 42.21

28.9 PAC 45.66
Other Boiler or Control Device Operating Parameters (e.g., Boiler O2) 

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

225.2

219.6

212

215.2

217

209.4

209.7

211

208.8

210

207.7

224.3

210.9

208.5

207.5

205.8

206.2

206.5

211.7

211.2

209.6

207.9

208.5

207.3

210.9

220.5

212.3

206.3

207.6

210.9
Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%)

3.2 11.2 17

3.2 10.9 17

3.3 10.9 17

3 11.2 17

3.2 11.2 17

3.8 10.7 17

3.4 11 17

3.1 11.2 17

3.1 11.2 17

2.9 11.3 17

2.8 11.3 17

7.4 7.7 17

3 11.1 17

2.7 11.5 17

2.7 11.6 17

2.6 11.7 17

2.6 11.6 17

2.7 11.4 17

2.8 11.4 17

2.8 11.5 17

2.5 11.7 17

2.5 11.7 17

2.7 11.4 17

2.6 11.5 17

2.6 11.6 17

3.2 11.2 17

2.7 11.4 17

2.6 11.5 17

2.7 11.4 17

2.6 11.4 17