Facility_Information

facility_id utility_codelegal_owner_nam legl_operator_name e legal_address_ty legal_address pe legal_city legal_state legal_zip

10071 56217 Cogentrix-Virginia Leas'g Corp Portsmouth Operating Services LLC legal owner9405 Arrowpoint Blvd Charlotte NC 28273

Page 1
Facility_Information

plant_namephysical_address phyical_cityphysical_statephysical_zipmailing_address mailing_citymailing_statemailing_zip

Cogentrix Virginia Leasing Corporation One Wild Duck Lane PortsmouthVA 23703 One Wild Duck Lane PortsmouthVA 23703

Page 2
Facility_Information

RFA_small_entity ff_fired_coalff_fired_oil ff_fired_ngasff_fired_petcoke ff_fired_other ff_permitted_coal ff_permitted_oil ff_permitted_ngas

No TRUE FALSE FALSE FALSE FALSE TRUE FALSE FALSE

Page 3
Facility_Information

ff_permitted_petcoke ff_permitted_other deviation_reporting continuous_emissions cem_providedfacility_note

FALSE FALSE Any event that causes excess emissions for more than one hour requires prompt deviation reporting(witNo Applicable NSPS: Subpart Db 

Page 4
facility_contacts

facility_id contact_id contact_titlecontact_namecontact_phone1 contact_phone2 contact_email contact_primary

10071 1 Compliance Supervisor Randy Musselwhite 757484354039 randymusselwhite@cogentrix.com FALSE

Page 5
facility_coal_utilized

facility_id coal_type percentage_mass percentage_btu synfuel_typecoal_note

10071 bituminous 100 100

Page 6
facility_oil_utilized

facility_id oil_type percentage_volume percentage_btu other_type

Page 7
facility_other_materials

facility_id other_material permitted_burn actually_burnother_quantity other_quantity other_note _units rcra_utilize rcra_explain

Page 8
facility_other_materials

rcra_explain

Page 9
boiler_information

facility_id boiler_id boiler_type boiler_otherbottom_design design_fuelheat_input max_heat_input MWe_capacity

10071 1A Stoker - underfeed Dry Bottomcoal 200 200 19.17

10071 1B Stoker - underfeed Dry Bottomcoal 200 200 19.17

10071 1C Stoker - underfeed Dry Bottomcoal 200 200 19.17

10071 2A Stoker - underfeed Dry Bottomcoal 200 200 19.17

10071 2B Stoker - underfeed Dry Bottomcoal 200 200 19.17

10071 2C Stoker - underfeed Dry Bottomcoal 200 200 19.17

Page 10
boiler_information

MWe_net_capacity design_gross_efficiency operating_gross_efficiency design_pressure operating_pressure design_tempoperating_temp design_reheat_multiple design_reheat_temp1

19.17 84.5 85.1 1500 1500 950 950 FALSE

19.17 84.5 85.1 1500 1500 950 950 FALSE

19.17 84.5 85.1 1500 1500 950 950 FALSE

19.17 84.5 85.1 1500 1500 950 950 FALSE

19.17 84.5 85.1 1500 1500 950 950 FALSE

19.17 84.5 85.1 1500 1500 950 950 FALSE

Page 11
boiler_information

design_reheat_temp2 operating_reheat_multiple operating_reheat_temp1 operating_reheat_temp2 hours_operatedvg_capacityapplicable_NSPS _factor retirement_yretirement_y ear ear_CBI

FALSE 5981 70.2 2028 FALSE

FALSE 5909 68.3 2028 FALSE

FALSE 5896 68 2028 FALSE

FALSE 5669 67.4 2028 FALSE

FALSE 5566 65.3 2028 FALSE

FALSE 5740 64.7 2028 FALSE

Page 12
boiler_information

NOx_controlSO2_controlcombustion_additives

Yes No No

Yes No No

Yes No No

Yes No No

Yes No No

Yes No No

Page 13
boiler_fuels

facility_id boiler_id fuel_type fuel_year percentage_massvol percentage_btu other_type

10071 1A coal - bituminous2007 100 100

10071 1A coal - bituminous2008 100 100

10071 1A coal - bituminous2009 100 100

10071 1B coal - bituminous2007 100 100

10071 1B coal - bituminous2008 100 100

10071 1B coal - bituminous2009 100 100

10071 1C coal - bituminous2007 100 100

10071 1C coal - bituminous2008 100 100

10071 1C coal - bituminous2009 100 100

10071 2A coal - bituminous2007 100 100

10071 2A coal - bituminous2008 100 100

10071 2A coal - bituminous2009 100 100

10071 2B coal - bituminous2007 100 100

10071 2B coal - bituminous2008 100 100

10071 2B coal - bituminous2009 100 100

10071 2C coal - bituminous2007 100 100

10071 2C coal - bituminous2008 100 100

10071 2C coal - bituminous2009 100 100

Page 14
boiler_control_NOx

facility_id boiler_id NOx_type NOx_other NOx_online

10071 1A Advanced Overfire Air 4/1/2003

10071 1B Advanced Overfire Air 4/1/2003

10071 1C Advanced Overfire Air 4/1/2003

10071 2A Advanced Overfire Air 4/1/2003

10071 2B Advanced Overfire Air 4/1/2003

10071 2C Advanced Overfire Air 4/1/2003

Page 15
boiler_control_SO2

facility_id boiler_id SO2_type SO2_other SO2_online

Page 16
boiler_additives

facility_id boiler_id boiler_additive additive_other additive_online

Page 17
facility_units

facility_id unit_id

10071 GEN1

10071 GEN2

Page 18
unit_boilers

facility_id unit_id boiler_id

10071 GEN1 1A

10071 GEN1 1B

10071 GEN1 1C

10071 GEN2 2A

10071 GEN2 2B

10071 GEN2 2C

Page 19
facility_controls

facility_id control_id control_groupcontrol_typecontrol_otherlegacy_control cntrol_onlinecontrol_offlineNOx_reagent

10071 BH1A PM control Fabric Filter, pulse FALSE 6/1/1988

10071 BH1B PM control Fabric Filter, pulse FALSE 6/1/1988

10071 BH1C PM control Fabric Filter, pulse FALSE 6/1/1988

10071 BH2A PM control Fabric Filter, pulse FALSE 6/1/1988

10071 BH2B PM control Fabric Filter, pulse FALSE 6/1/1988

10071 BH2C PM control Fabric Filter, pulse FALSE 6/1/1988

10071 FGD1A SO2 controlSpray dryer type FALSE 4/1/2008

10071 FGD1B SO2 controlSpray dryer type FALSE 4/1/2008

10071 FGD1C SO2 controlSpray dryer type FALSE 4/1/2008

10071 FGD2A SO2 controlSpray dryer type FALSE 10/1/2007

10071 FGD2B SO2 controlSpray dryer type FALSE 10/1/2007

10071 FGD2C SO2 controlSpray dryer type FALSE 10/1/2007

Page 20
facility_controls

reagent_other NOx_ammonia SO2_sorbent oher_sorbent SO2_scrubber_additive

Lime and alkaline fly ashNo

Lime and alkaline fly ashNo

Lime and alkaline fly ashNo

Lime and alkaline fly ashNo

Lime and alkaline fly ashNo

Lime and alkaline fly ashNo

Page 21
facility_sampling_ports

facility_id sampling_port_id

10071 SP1

10071 SP2

Page 22
facility_stacks

facility_id stack_id stack_heightstack_diameter sack_gas_velocity

10071 UNIT1 198 8.7 53

10071 UNIT2 198 8.7 53

Page 23
configurations

facility_id configuration_id

10071 GEN1

10071 GEN2

Page 24
configuration_components

facility_id configuration_id component_idorder component_ty port_near pe

10071 GEN1 BH1A 3 PM control

10071 GEN1 BH1B 3 PM control

10071 GEN1 BH1C 3 PM control

10071 GEN1 FGD1A 2 SO2 control

10071 GEN1 FGD1B 2 SO2 control

10071 GEN1 FGD1C 2 SO2 control

10071 GEN1 GEN1 1 Unit

10071 GEN1 SP1 4 Sampling Port next

10071 GEN1 UNIT1 5 Stack

10071 GEN2 BH2A 3 PM control

10071 GEN2 BH2B 3 PM control

10071 GEN2 BH2C 3 PM control

10071 GEN2 FGD2A 2 SO2 control

10071 GEN2 FGD2B 2 SO2 control

10071 GEN2 FGD2C 2 SO2 control

10071 GEN2 GEN2 1 Unit

10071 GEN2 SP2 4 Sampling Port next

10071 GEN2 UNIT2 5 Stack

Page 25
configuration_pollutants1

facility_id configuration_id pollutant_nampermit_ty e pe_1emlimit_1 emlimit_units_1 avg_period_1emlimit_2 emlimit_units_2

10071 GEN1 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.6 pound per million British Thermal Unit (lb/MMBtu) 30 days

10071 GEN1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 0.96 pound per million British Thermal Unit (lb/MMBtu) 30 days

10071 GEN1 PM (Filterable) Fderal - Title V Operating Permit 0.03 pound per million British Thermal Unit (lb/MMBtu)

10071 GEN1 VOCs Federal - Title V Operating Permit 0.003 pound per million British Thermal Unit (lb/MMBtu)

10071 GEN1 Carbon Monoxide (CO) Federal - Title V Operating Permit 0.6 pound per million British Thermal Unit (lb/MMBtu)

10071 GEN2 PM (Filterable) Fderal - Title V Operating Permit 0.03 pound per million British Thermal Unit (lb/MMBtu)

10071 GEN2 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.6 pound per million British Thermal Unit (lb/MMBtu) 30 days

10071 GEN2 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 0.96 pound per million British Thermal Unit (lb/MMBtu) 30 days

10071 GEN2 VOCs Federal - Title V Operating Permit 0.003 pound per million British Thermal Unit (lb/MMBtu)

10071 GEN2 Carbon Monoxide (CO) Federal - Title V Operating Permit 0.6 pound per million British Thermal Unit (lb/MMBtu)

Page 26
configuration_pollutants1

avg_period_2emlimit_3 emlimit_units_3 avg_period_3emlimit_4 emlimit_units_4 avg_period_4emlimit_details test_method

 Unit (lb/MMBtu) Method 5

 Unit (lb/MMBtu)

 Unit (lb/MMBtu)

 Unit (lb/MMBtu) Method 5

 Unit (lb/MMBtu)

 Unit (lb/MMBtu)

Page 27
configuration_pollutants1

emrate emrate_unitsguarantee_level_explainreq_monitoringeq_recordkeeping req_reporting

Continous Emissions Monitoring CEMS data per Part 60 Quarterly Report per Part 60

Continuos Emissions Monitoring CEMS data per Part 60 Quarterly Report per Part60

5 Year Stack Test File Copy of Stack Test Results Submit copy of stack test results to VDEQ

5 Year Stack Test File Copy of Stack Test Results Submit copy of stack test results to VDEQ

5 Year Stack Test File Copy of Stack Test Results Submit copy of stack test results to VDEQ

Five Year Stack Test File copy of stack test results Submit copy of stack test results to VDEQ

Continuos Emissions Monitoring CEMS data per Part 60 Quarterly Report per Part 60

Continuous Emissions Monitoring CEMS data per Part 60 Quarterly Report per Part 60

Five Year Stack Test File copy of stack test results Submit copy of stack test results to VDEQ

Five Year Stack Test File copy of stack test results Submit copy of stack test results to VDEQ

Page 28
configuration_pollutants1

test results to VDEQ

test results to VDEQ

test results to VDEQ

test results to VDEQ

test results to VDEQ

test results to VDEQ

Page 29
control_technologies

facility_id configuration_id component_idcontrol_id project_titleproject_typevendor_namevndor_contact vendor_phone

Page 30
control_technologies

vendor_address vndor_cityvendor_statevendor_zip actual_start_date projected_start_date end_date sorbent chemical_additive

Page 31
control_technologies

injection_point HAP_emission_reduction HAP_emission_rate HAP_emission_rate_units HAP_achieved_reduction HAP_achieved_rate HAP_achieved_rate_units feed_rate feed_rate_units

Page 32
control_technologies

feed_rate_units

Page 33
control_coal_ranks

facility_id configuration_id component_idcontrol_id coal_type

Page 34
control_pollutants1

facility_id configuration_id component_idcontrol_id pollutant_name

Page 35
control_costs

facility_id configuration_id component_idcontrol_id boiler_retrofit boiler_new_install total_capital_investm total_operating_costs entbase_year

Page 36
control_costs

CBI

Page 37
misc_controls

facility_id misc_control_id control_description

Page 38
misc_control_configurations

facility_id misc_control_id configuration_id

Page 39
fuel_shipments

facility_id shipment_idshipment_date amount_received amount_unitsfuel_type state_countryother_countrycounty

10071 April 4/1/2009 9921 short tons (2000 lbs) coal WV

10071 August 8/1/2009 4972 short tons (2000 lbs) coal WV

10071 December 12/1/2009 13122 short tons (2000 lbs) coal WV

10071 February 2/1/2009 9965 short tons (2000 lbs) coal WV

10071 January 1/1/2009 24993 short tons (2000 lbs) coal WV

10071 June 6/1/2009 5021 short tons (2000 lbs) coal WV

10071 March 3/1/2009 5009 short tons (2000 lbs) coal WV

Page 40
fuel_shipments

coal_seam shipment_method

Barge

Barge

Barge

Barge

Barge

Barge

Barge

Page 41
fuel_shipment_configurations

facility_id shipment_idconfiguration_id

10071 April GEN1

10071 April GEN2

10071 August GEN1

10071 August GEN2

10071 December GEN1

10071 December GEN2

10071 February GEN1

10071 February GEN2

10071 January GEN1

10071 January GEN2

10071 June GEN1

10071 June GEN2

10071 March GEN1

10071 March GEN2

Page 42
fuel_shipment_samples

facility_id shipment_idsample_id amount_fuelamount_fuel_units total_sulfur ash_contentheating_valuehating_units

Page 43
fuel_shipment_samples

chlorine chlorine_unitsfluorine fluorine_unitsdata_provideddata_other_specified supplier_typesupplier_name supplier_address

Page 44
fuel_shipment_samples

supplier_citysupplier_statesupplier_ziplab_name lab_addresslab_city lab_state lab_zip analysis_copies

Page 45
fuel_shipment_samples

analysis_copies

Page 46
fuel_sample_pollutants

facility_id shipment_idsample_id fuel_pollutant pollutant_conc pollutant_conc_units pollutant_conc_ND pollutant_conc_MDL

Page 47
test_reports

facility_id report_id report_typeother_type report_description report_begin_date report_end_date before_control during_deviation

10071 March 2007 Emissions Test compliance March 2007 Compliance Testing per Facility 3/1/2007 3/2/2007 No Title 5 Permit No

Page 48
test_reports

deviation_reports

No

Page 49
test_report_configurations

facility_id report_id configuration_id

10071 March 2007 Emissions Test GEN1

Page 50
test_report_fuels

facility_id report_id fuel_id

10071 March 2007 Emissions Test Coal

Page 51
test_report_fuel_types

facility_id report_id fuel_id fuel_type percentage_massvol percentage_btu other_type

10071 March 2007 Emissions Test Coal coal - bituminous 100 100

Page 52
cem_data

facility_id time_periodcem_period_description

Page 53
cem_data_pollutants1

facility_id time_periodpollutant_name

Page 54
test_report_sampling

facility_id report_id sampling_port_id point_differpoint_description befre_SO2_device point_orientation normal_bypass_percent testing_bypass_percent

10071 March 2007 Emissions Test SP1 Yes Note that the SO2 control equipment was not installed at the time that this stack No

Page 55
test_report_sampling

fg_fraction

100%

Page 56
sampling_runs

facility_id report_id sampling_port_id run_id start_datetime end_datetimunit_load e net_generation fg_moisture_content

10071 March 2007 Emissions Test SP1 1 3/1/2007 3/1/2007 54 108 6.33

10071 March 2007 Emissions Test SP1 2 3/1/2007 3/1/2007 53.4 106.8 6.75

10071 March 2007 Emissions Test SP1 3 3/2/2007 3/2/2007 52.9 105.8 7.07

Page 57
sampling_runs

fg_flow_ratefg_flow_rate_units standard_temperature standard_pressure normal_temperature normal_pressure fg_oxygen_content fg_CO2_content fg_temperature

146395 dscfm 68 1 7 12.11 277

146564 dscfm 68 1 7.03 12.15 276

141862 dscfm 68 1 6.54 12.69 283

Page 58
sampling_runs

fg_pressureHg_loi test_methodrun_comments fuel_id fuel_unit_loadfuel_flow_ratefuel_ash fuel_heating_value

1.006 Methods 5, 6C, 10 & 25A

1.008 Methods 5, 6C, 10 & 25A

1.012 Methods 5, 6C, 10 & 25A

Page 59
sampling_runs

fuel_sulfur

Page 60
sampling_run_pollutants1

facility_id report_id sampling_port_id run_id pollutant_namconce conc_units conc_ND conc_MDL

10071 March 2007 Emissions Test SP1 1 PM (Filterable) 0.0014 FALSE

10071 March 2007 Emissions Test SP1 1 Carbon Monoxide (CO) 89.3 parts per million by FALSE volume (dry) (ppmvd)

10071 March 2007 Emissions Test SP1 1 Sulfur Dioxide (SO2) 458.8 parts per million by FALSE volume (dry) (ppmvd)

10071 March 2007 Emissions Test SP1 1 VOCs 1.7 parts per million by FALSE volume (dry) (ppmvd)

10071 March 2007 Emissions Test SP1 2 PM (Filterable) 0.0014 FALSE

10071 March 2007 Emissions Test SP1 2 Carbon Monoxide (CO) 107.1 parts per million by FALSE volume (dry) (ppmvd)

10071 March 2007 Emissions Test SP1 2 Sulfur Dioxide (SO2) 465.2 parts per million by FALSE volume (dry) (ppmvd)

10071 March 2007 Emissions Test SP1 2 VOCs 3.1 parts per million by FALSE volume (dry) (ppmvd)

10071 March 2007 Emissions Test SP1 3 PM (Filterable) 0.0018 FALSE

10071 March 2007 Emissions Test SP1 3 Carbon Monoxide (CO) 269.9 parts per million by FALSE volume (dry) (ppmvd)

10071 March 2007 Emissions Test SP1 3 Sulfur Dioxide (SO2) 481.1 parts per million by FALSE volume (dry) (ppmvd)

10071 March 2007 Emissions Test SP1 3 VOCs 6.5 parts per million by FALSE volume (dry) (ppmvd)

Page 61
sampling_run_pollutants1

emission_rateemission_rate_units emission_rate_ND emission_rate_MDL emission_factor emission_factor_units emission_factor_ND emission_factor_MDL run_pollutant_comment

1.8 pound per hour (lb/hr) FALSE 0.003 pound per million British Thermal Unit (lb/MMBtu) FALSE units - gr/dscf

57.01 pound per hour (lb/hr) FALSE 0.097 pound per million British Thermal Unit (lb/MMBtu) FALSE

670.02 pound per hour (lb/hr) FALSE 1.134 pound per million British Thermal Unit (lb/MMBtu) FALSE Testing performed when SO2 perm

0.46 pound per hour (lb/hr) FALSE 0.0008 pound per million British Thermal Unit (lb/MMBtu) FALSE

1.73 pound per hour (lb/hr) FALSE 0.0029 pound per million British Thermal Unit (lb/MMBtu) FALSE Units - gr/dscf

68.46 pound per hour (lb/hr) FALSE 0.115 pound per million British Thermal Unit (lb/MMBtu) FALSE

680.15 pound per hour (lb/hr) FALSE 1.146 pound per million British Thermal Unit (lb/MMBtu) FALSE Testing performed when SO2 perm

0.85 pound per hour (lb/hr) FALSE 0.0014 pound per million British Thermal Unit (lb/MMBtu) FALSE

2.23 pound per hour (lb/hr) FALSE 0.0037 pound per million British Thermal Unit (lb/MMBtu) FALSE Units - gr/dscf

166.99 pound per hour (lb/hr) FALSE 0.278 pound per million British Thermal Unit (lb/MMBtu) FALSE

680.83 pound per hour (lb/hr) FALSE 1.134 pound per million British Thermal Unit (lb/MMBtu) FALSE Testing performed when SO2 perm

1.72 pound per hour (lb/hr) FALSE 0.0029 pound per million British Thermal Unit (lb/MMBtu) FALSE

Page 62
sampling_run_pollutants1

run_pollutant_comment

units - gr/dscf

Testing performed when SO2 permit limit was 1.52 lbs/mmBTU

Units - gr/dscf

Testing performed when SO2 permit limit was 1.52 lbs/mmBTU

Units - gr/dscf

Testing performed when SO2 permit limit was 1.52 lbs/mmBTU

Page 63
sampling_run_fuel

facility_id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_NDfuel_conc_MDL

Page 64
sampling_run_fuel

fuel_conc_MDL

Page 65