5A-i 

### APPENDIX 5A. ENG INEERING RESULTS USED IN THE SHIPMENTS, NATIONAL IMPACTS, AND LIFE-CYCLE COST SUBGROUP ANALYSES

TABLE OF CONTENTS

5A.1 INTRODUCTION .................................................................................................. 5A-1 5A.2 GENERAL SERVICE FLUORESCENT LAMPS................................................. 5A-1 5A.2.1 Systems Used in the Shipments Analysis and NIA .................................... 5A-1 5A.2.1.1 4-foot Medium Bipin General Service Fluorescent Lamps ............ 5A-2 5A.2.1.2 8-foot Single Pin Slimline Genera l Service Fluorescent Lamps .... 5A-6 5A.2.1.3 8-foot Recessed Double Contact High Output General Service Fluorescent Lamps.......................................................................... 5A-8 5A.2.1.4 4-foot T5 Miniature Bipin St andard Output General Service Fluorescent Lamps........................................................................ 5A-10 5A.2.1.5 4-foot T5 Miniature Bipi n High Output General Service Fluorescent Lamps........................................................................ 5A-11 5A.2.2 Systems Used by Consumers of T12 Electronic Ballasts ......................... 5A-12 5A.2.2.1 4-foot Medium Bipin General Service Fluorescent Lamps .......... 5A-12 5A.2.2.2 8-foot Single Pin Slimline Genera l Service Fluorescent Lamps .. 5A-14 5A.2.2.3 8-foot Recessed Double Contact High Output General Service Fluorescent Lamps........................................................................ 5A-15 5A.3 INCANDESCENT REFLECTOR LAMPS.......................................................... 5A-16

LIST OF TABLES

Table 5A.2.1 4-foot T8 Medium Bipin 3-Lamp s per Ballast Lamp -and-Ballast Designs in the Commercial Sector ................................................................................ 5A-2 Table 5A.2.2 4-foot T12 Medium Bipin Lamp -and-Ballast De signs in the Commercial Sector .......................................................................................................... 5A-3 Table 5A.2.3 4-foot T8 Medium Bipin 2-Lamp s per Ballast Lamp -and-Ballast Designs in the Commercial and Residential Sector ...................................................... 5A-3 Table 5A.2.4 4-foot T12 Medium Bipin 2-La mps per Ballast Lam p-and-Ballast Designs in the Residential Sector ............................................................................. 5A-5 Table 5A.2.5 8-foot T8 Single Pin Slimline 2-Lamps per Ballast Lamp-and-Ballast Designs in the Commer cial Sector .............................................................. 5A-6 Table 5A.2.6 8-foot T12 Single Pin Slimlin e 2-Lamps per Ballast Lamp-and-Ballast Designs in the Comm ercial Sector .............................................................. 5A-7 Table 5A.2.7 8-foot T8 Recessed Double C ontact High Output 2-Lamps per Ballast Lam p-and-Ballast Designs in the Industrial Sector .................................... 5A-8 Table 5A.2.8 8-foot T12 Recessed Double C ontact High Ou tput 2-Lamps per Ballast Lamp-and-Ballast Designs in the Industrial Sector .................................... 5A-9 Table 5A.2.9 4-foot T5 Miniature Bipin St andard Output 2-Lamps per Ballast Lampand-Ballast Designs in the Comm ercial Sector ........................................ 5A-10 Table 5A.2.10 4-foot T5 Mini ature Bipin High Output 2- Lamps per Ballast Lamp-andBallas t Designs in the Industrial Sector .................................................... 5A-115A-ii 

### Table 5A.2.11 4-foot T8 Medium Bipin 3-La mps per Ballast Lamp-and-Ballast Designs in the Commercial and Industrial Sectors ................................................. 5A-12 Table 5A.2.12 4-foot T12 Medium Bipin 3-La mps per Ballast Lamp-and-Ballast Designs in the Comm ercial and Industrial Sectors ................................................. 5A-12 Table 5A.2.13 4-foot T8 Medium Bipin 2-La mps per Ballast Lam p-and-Ballast Designs in the Residential Sector ........................................................................... 5A-13 Table 5A.2.14 4-foot T12 Medium Bipin 2-La mps per Ballast Lamp-and-Ballast Designs in the Res idential Sector ........................................................................... 5A-13 Table 5A.2.15 8-foot T8 Single Pin Slimlin e 2-Lamp s per Ballast Lamp-and-Ballast Designs in the Commercial and Industrial Sectors ................................... 5A-14 Table 5A.2.16 8-foot T12 Single Pin Slimlin e 2-Lamp s per Ballast Lamp-and-Ballast Designs in the Commercial and Industrial Sectors ................................... 5A-14 Table 5A.2.17 8-foot T8 Recessed Double C ontact High Ou tput 2-Lamps per Ballast Lamp-and-Ballast Designs in the Industrial Sector .................................. 5A-15 Table 5A.2.18 8-foot T12 Recessed Double C ontact High Ou tput 2-Lamps per Ballast Lamp-and-Ballast Designs in the Industrial Sector .................................. 5A-15 Table 5A.3.1 90W PAR38 Incandescent Reflector Lamps ................................................... 5A-16 Table 5A.3.2 75W PAR38 Incandescent Reflector Lamps ................................................... 5A-17 Table 5A.3.3 50W PAR30 Incandescent Reflector Lamps ................................................... 5A-185A-1 

### APPENDIX 5A. ENGINEERING RESULTS USED IN THE SHIPMENTS, NATIONAL IMPACTS, AND LIFE-CYCLE CO ST SUBG ROUP ANALYSES

5A.1 INTRODUCTION

This append ix presents some additional engineering results used in the shipments analysis, national impacts analys is (NIA), and life-cycle cost (LCC) subgroup analysis. In addition to many of the lamp and lamp-and-ballast designs considered in the primary LCC and payback period (PBP) analysis, the shipments an alysis and national impact analysis (NIA) includes designs that do not save energy or do not emit lumens with in 10 percent of the baseline lamp-and-ballast system. Product substitutions li ke reflector compact fluorescent lamps (CFL) that are not included in the LCC and PBP analysis are also considered in the NIA and shipments analysis. Furthermore, the LCC subgroup anal ysis contains an assessment of LCC and PBP results for consumers of fluorescent T12 electro nic baseline lamp-and-ballast systems, and the engineering results for those system s are presented in this appendix.

5A.2 GENERAL SERVICE FLUORESCENT LAMPS

5A.2.1 Systems Used in the Shipments Analysis and NIA
The following tables list the lam p-and-ball ast designs used in the general service fluorescent lamp (GSFL) shipments analysis and th e NIA. In addition to many of the lamp-andballast designs considered in the LCC and PBP an alysis, the shipments analysis and NIA include designs that do not save energy or do not emit lumens within 10 percent of the baseline lampand-ballast system.5A-2 

### 5A.2.1.1 4-foot Medium Bipin General Service Fluorescent Lamps
Table 5A.2.1 4-foot T8 Medium Bipin 3-Lamps per Ballast Lamp-and-Ballast Designs in the Commercial SectorRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

2 32.5 86.2 2,802 2,520 20,000 Electronic 0.88 86.8 7,396 6,653

3 32.5 90.8 2,951 2,710 20,000 Electronic 0.88 86.8 7,791 7,154

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.88 86.8 7,919 7,524

5 32.5 95.4 3,101 2,915 24,000 Electronic 0.88 86.8 8,185 7,696

4 30.4 93.8 2,852 2,680 20,000 Electronic 0.88 80.4 7,528 7,075

5 28.4 96.0 2,726 2,560 18,000 Electronic 0.88 69.7 7,198 6,758

4 26.6 93.0 2,474 2,350 30,000 Electronic 0.88 66.5 6,531 6,204

2 32.5 86.2 2,802 2,520 20,000 Electronic 0.78 77.9 6,556 5,897

3 32.5 90.8 2,951 2,710 20,000 Electronic 0.78 77.9 6,905 6,341

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.78 77.9 7,019 6,669

5 32.5 95.4 3,101 2,915 24,000 Electronic 0.78 77.9 7,255 6,821

4 30.4 93.8 2,852 2,680 20,000 Electronic 0.78 72.2 6,673 6,271

5 28.4 96.0 2,726 2,560 18,000 Electronic 0.78 67.0 6,380 5,990

4 26.6 93.0 2,474 2,350 30,000 Electronic 0.78 59.4 5,789 5,499

2 32.5 86.2 2,802 2,520 20,000 Electronic 0.71 71.7 5,967 5,368

3 32.5 90.8 2,951 2,710 20,000 Electronic 0.71 71.7 6,286 5,772

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.71 71.7 6,389 6,071

5 32.5 95.4 3,101 2,915 24,000 Electronic 0.71 71.7 6,604 6,209

4 30.4 93.8 2,852 2,680 20,000 Electronic 0.71 66.4 6,074 5,708

5 28.4 96.0 2,726 2,560 18,000 Electronic 0.71 61.6 5,807 5,453

4 26.6 93.0 2,474 2,350 30,000 Electronic 0.71 54.5 5,269 5,006 * All systems use 3 lamps per ballast.5A-3 

### Table 5A.2.2 4-foot T12 Medium Bipin Lamp -and-Ballast Designs in the Commercial SectorRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

0 41.0 78.0 3,198 2,880 20,000 Magnetic 0.95 129.0 9,114 8,208

1 41.0 80.5 3,301 3,000 20,000 Magnetic 0.95 129.0 9,406 8,550

1 41.0 82.9 3,399 3,060 24,000 Magnetic 0.95 129.0 9,687 8,721

2 41.0 87.8 3,600 3,250 24,000 Magnetic 0.95 129.0 10,259 9,263

0 34.0 77.9 2,649 2,300 20,000 Magnetic 0.88 108.0 6,992 6,072

1 34.0 82.4 2,802 2,460 20,000 Magnetic 0.88 108.0 7,396 6,494

2 34.0 85.3 2,900 2,610 20,000 Magnetic 0.88 108.0 7,657 6,890

3 34.0 91.2 3,101 2,790 24,000 Magnetic 0.88 108.0 8,186 7,366

0 41.0 78.0 3,198 2,880 20,000 Electronic 0.88 107.7 8,443 7,603

1 41.0 80.5 3,301 3,000 20,000 Electronic 0.88 107.7 8,713 7,920

1 41.0 82.9 3,399 3,060 24,000 Electronic 0.88 107.7 8,973 8,078

2 41.0 87.8 3,600 3,250 24,000 Electronic 0.88 107.7 9,503 8,580

0 34.0 77.9 2,649 2,300 20,000 Electronic 0.88 91.7 6,992 6,072

1 34.0 82.4 2,802 2,460 20,000 Electronic 0.88 91.7 7,396 6,494

2 34.0 85.3 2,900 2,610 20,000 Electronic 0.88 91.7 7,657 6,890

3 34.0 91.2 3,101 2,790 24,000 Electronic 0.88 91.7 8,186 7,366

0 41.0 78.0 3,198 2,880 20,000 Electronic 0.86 106.3 8,251 7,430

1 41.0 80.5 3,301 3,000 20,000 Electronic 0.86 106.3 8,515 7,740

1 41.0 82.9 3,399 3,060 24,000 Electronic 0.86 106.3 8,769 7,895

2 41.0 87.8 3,600 3,250 24,000 Electronic 0.86 106.3 9,287 8,385

0 34.0 77.9 2,649 2,300 20,000 Electronic 0.86 90.3 6,833 5,934

1 34.0 82.4 2,802 2,460 20,000 Electronic 0.86 90.3 7,228 6,347

2 34.0 85.3 2,900 2,610 20,000 Electronic 0.86 90.3 7,483 6,734

3 34.0 91.2 3,101 2,790 24,000 Electronic 0.86 90.3 8,000 7,198 * All electronic systems use 3 lamps per ballast. All magnetic systems use a 2-lamp ballast and a 1-lamp ballast.



### Table 5A.2.3 4-foot T8 Medium Bipin 2-Lamps per Ballast Lamp-and-Ballast Designs in the Commercial and Residential Sector5A-4Rated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

2 32.5 86.2 2,802 2,520 20,000 Electronic 0.88 58.6 4,931 4,435

3 32.5 90.8 2,951 2,710 20,000 Electronic 0.88 58.6 5,194 4,770

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.88 58.6 5,280 5,016

5 32.5 95.4 3,101 2,915 24,000 Electronic 0.88 58.6 5,457 5,130

4 30.4 93.8 2,852 2,680 20,000 Electronic 0.88 54.6 5,019 4,717

5 28.4 96.0 2,726 2,560 18,000 Electronic 0.88 51.2 4,798 4,506

4 26.6 93.0 2,474 2,350 30,000 Electronic 0.88 45.4 4,354 4,136

2 32.5 86.2 2,802 2,520 20,000 Electronic 0.78 51.6 4,370 3,931

3 32.5 90.8 2,951 2,710 20,000 Electronic 0.78 51.6 4,604 4,228

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.78 51.6 4,680 4,446

5 32.5 95.4 3,101 2,915 24,000 Electronic 0.78 51.6 4,837 4,547

4 30.4 93.8 2,852 2,680 20,000 Electronic 0.78 48.9 4,448 4,181

5 28.4 96.0 2,726 2,560 18,000 Electronic 0.78 45.6 4,253 3,994

4 26.6 93.0 2,474 2,350 30,000 Electronic 0.78 40.5 3,859 3,666

2 32.5 86.2 2,802 2,520 20,000 Electronic 0.71 46.8 3,978 3,578

3 32.5 90.8 2,951 2,710 20,000 Electronic 0.71 46.8 4,190 3,848

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.71 46.8 4,260 4,047

5 32.5 95.4 3,101 2,915 24,000 Electronic 0.71 46.8 4,403 4,139

4 30.4 93.8 2,852 2,680 20,000 Electronic 0.71 44.9 4,049 3,806

5 28.4 96.0 2,726 2,560 18,000 Electronic 0.71 41.7 3,871 3,635

4 26.6 93.0 2,474 2,350 30,000 Electronic 0.71 37.0 3,513 3,337 * All systems use 2 lamps per ballast.5A-5 

### Table 5A.2.4 4-foot T12 Medium Bipin 2-Lamp s per Ballast Lamp-and-Ballast Designs in the Residential SectorRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

1 34.0 82.4 2,802 2,460 20,000 Electronic 0.75 48.0 4,202 3,690

2 34.0 85.3 2,900 2,610 20,000 Electronic 0.75 48.0 4,350 3,915

3 34.0 91.2 3,101 2,790 24,000 Electronic 0.75 48.0 4,651 4,185

0 41.0 76.8 3,149 2,860 15,000 Magnetic 0.68 70.0 4,282 3,890

0 41.0 80.5 3,301 3,000 20,000 Magnetic 0.68 70.0 4,489 4,080

1 41.0 82.9 3,399 3,060 24,000 Magnetic 0.68 70.0 4,623 4,162

2 41.0 87.8 3,600 3,250 24,000 Magnetic 0.68 70.0 4,896 4,420

1 34.0 82.4 2,802 2,460 20,000 Magnetic 0.66 60.0 3,698 3,247

2 34.0 85.3 2,900 2,610 20,000 Magnetic 0.66 60.0 3,828 3,445

3 34.0 91.2 3,101 2,790 24,000 Magnetic 0.66 60.0 4,093 3,683

0 41.0 76.8 3,149 2,860 15,000 Electronic 0.65 58.0 4,093 3,718

0 41.0 80.5 3,301 3,000 20,000 Electronic 0.65 58.0 4,291 3,900

1 41.0 82.9 3,399 3,060 24,000 Electronic 0.65 58.0 4,419 3,978

2 41.0 87.8 3,600 3,250 24,000 Electronic 0.65 58.0 4,680 4,225 * All systems use 2 lamps per ballast.5A-6 

### 5A.2.1.2 8-foot Single Pin Slimline Ge neral Service Fluo rescent Lamps

Table 5A.2.5 8-foot T8 Single Pin Slimline 2- Lamps per Ballast Lamp-and-Ballast Designs in the Commercial SectorRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

3 60.1 94.8 5,697 5,130 15,000 Electronic 0.88 112.8 10,028 9,029

4 60.1 98.2 5,902 5,428 15,000 Electronic 0.88 112.8 10,387 9,553

5 60.1 101.5 6,100 5,795 18,000 Electronic 0.88 112.8 10,736 10,199

5 57.0 101.8 5,803 5,450 24,000 Electronic 0.88 107.5 10,213 9,592

5 55.0 103.6 5,698 5,415 18,000 Electronic 0.88 102.0 10,028 9,530

3 60.1 94.8 5,697 5,130 15,000 Electronic 0.85 109.1 9,686 8,721

4 60.1 98.2 5,902 5,428 15,000 Electronic 0.85 109.1 10,033 9,228

5 60.1 101.5 6,100 5,795 18,000 Electronic 0.85 109.1 10,370 9,852

5 57.0 101.8 5,803 5,450 24,000 Electronic 0.85 106.0 9,864 9,265

5 55.0 103.6 5,698 5,415 18,000 Electronic 0.85 98.5 9,687 9,206

5 57.0 101.8 5,803 5,450 24,000 Electronic 0.78 102.5 9,052 8,502

3 60.1 94.8 5,697 5,130 15,000 Electronic 0.78 100.4 8,888 8,003

4 60.1 98.2 5,902 5,428 15,000 Electronic 0.78 100.4 9,207 8,468

5 60.1 101.5 6,100 5,795 18,000 Electronic 0.78 100.4 9,516 9,040

5 55.0 103.6 5,698 5,415 18,000 Electronic 0.78 90.2 8,889 8,447 * All systems use 2 lamps per ballast.5A-7 

### Table 5A.2.6 8-foot T12 Single Pin Slimline 2-Lamps per Ballast Lamp-and-Ballast Designs in the Commercial SectorRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

0 75.0 85.6 6,420 5,906 12,000 Magnetic 0.94 158.0 12,070 11,103

1 75.0 87.3 6,548 6,157 12,000 Magnetic 0.94 158.0 12,309 11,575

2 75.0 92.0 6,900 6,370 15,000 Magnetic 0.94 158.0 12,972 11,976

0 75.0 85.6 6,420 5,906 12,000 Electronic 0.88 135.0 11,299 10,395

1 75.0 87.3 6,548 6,157 12,000 Electronic 0.88 135.0 11,524 10,836

2 75.0 92.0 6,900 6,370 15,000 Electronic 0.88 135.0 12,144 11,211

1 60.5 87.6 5,300 4,664 12,000 Magnetic 0.88 126.0 9,328 8,209

2 60.5 92.6 5,602 5,152 12,000 Magnetic 0.88 126.0 9,860 9,068

3 60.5 97.5 5,899 5,480 15,000 Magnetic 0.88 126.0 10,382 9,645

1 60.5 87.6 5,300 4,664 12,000 Electronic 0.88 110.0 9,328 8,209

2 60.5 92.6 5,602 5,152 12,000 Electronic 0.88 110.0 9,860 9,068

3 60.5 97.5 5,899 5,480 15,000 Electronic 0.88 110.0 10,382 9,645

0 75.0 85.6 6,420 5,906 12,000 Electronic 0.85 132.0 10,914 10,040

1 75.0 87.3 6,548 6,157 12,000 Electronic 0.85 132.0 11,131 10,467

2 75.0 92.0 6,900 6,370 15,000 Electronic 0.85 132.0 11,730 10,829

1 60.5 87.6 5,300 4,664 12,000 Electronic 0.85 107.0 9,010 7,929

2 60.5 92.6 5,602 5,152 12,000 Electronic 0.85 107.0 9,524 8,758

3 60.5 97.5 5,899 5,480 15,000 Electronic 0.85 107.0 10,028 9,316 * All systems use 2 lamps per ballast.5A-8 

### 5A.2 .1.3 8-foot Recessed Double Contact High Output General Service Fluorescent Lamps

Table 5A.2.7 8-foot T8 Recessed Double Contac t High Output 2-Lamps per Ballast Lamp

and-Ballast Designs in the Industrial SectorRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

4 86.0 91.9 7,903 7,100 24,000 Electronic 0.88 160.0 13,910 12,496

4 86.0 93.0 7,998 7,200 18,000 Electronic 0.88 160.0 14,076 12,672

5 86.0 95.3 8,196 7,800 18,000 Electronic 0.88 160.0 14,425 13,728

4 86.0 91.9 7,903 7,100 24,000 Electronic 0.81 151.0 12,804 11,502

4 86.0 93.0 7,998 7,200 18,000 Electronic 0.81 151.0 12,957 11,664

5 86.0 95.3 8,196 7,800 18,000 Electronic 0.81 151.0 13,277 12,636 * All systems use 2 lamps per ballast.5A-9 

### Table 5A.2.8 8-foot T12 Recessed Double Co ntact High Output 2-Lamps per Ballast Lamp-and-Ballast Designs in the Industrial SectorRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

0 113.0 80.1 9,051 8,145 12,000 Magnetic 0.95 237.0 17,197 15,476

1 113.0 83.2 9,402 8,648 12,000 Magnetic 0.95 237.0 17,863 16,431

0 97.0 82.5 8,003 6,950 12,000 Magnetic 0.91 203.0 14,565 13,205

2 97.0 86.1 8,352 7,515 12,000 Magnetic 0.91 203.0 15,200 14,279

3 97.0 87.6 8,497 7,650 12,000 Magnetic 0.91 203.0 15,465 14,535

3 97.0 88.9 8,623 7,750 12,000 Magnetic 0.91 203.0 15,694 14,725

0 113.0 80.1 9,051 8,145 12,000 Electronic 0.90 211.5 16,292 14,661

1 113.0 83.2 9,402 8,648 12,000 Electronic 0.90 211.5 16,923 15,566

0 97.0 82.5 8,003 6,950 12,000 Electronic 0.90 185.6 14,405 12,510

2 97.0 86.1 8,352 7,515 12,000 Electronic 0.90 185.6 15,033 13,527

3 97.0 87.6 8,497 7,650 12,000 Electronic 0.90 185.6 15,295 13,770

3 97.0 88.9 8,623 7,750 12,000 Electronic 0.90 185.6 15,522 13,950

0 113.0 80.1 9,051 8,145 12,000 Electronic 0.88 205.4 15,930 14,335

1 113.0 83.2 9,402 8,648 12,000 Electronic 0.88 205.4 16,547 15,220

0 97.0 82.5 8,003 6,950 12,000 Electronic 0.88 177.0 14,084 12,232

2 97.0 86.1 8,352 7,515 12,000 Electronic 0.88 177.0 14,699 13,226

3 97.0 87.6 8,497 7,650 12,000 Electronic 0.88 177.0 14,955 13,464

3 97.0 88.9 8,623 7,750 12,000 Electronic 0.88 177.0 15,177 13,640 * All systems use 2 lamps per ballast.5A-10 

### 5A.2 .1.4 4-foot T5 Miniature Bipin Standard Output General Service Fluorescent Lamps

Table 5A.2.9 4-foot T5 Miniat ure Bipin Standard Output 2-Lamps per Ballast Lamp-andBallast Designs in the Commercial SectorRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

0 27.8 86.0 2,391 1,650 20,000 Electronic 1.15 70.7 5,499 3,795

1 27.8 104.3 2,900 2,660 20,000 Electronic 1.15 70.7 6,669 6,118

2 27.8 109.7 3,050 2,898 20,000 Electronic 1.15 70.7 7,014 6,665

2 26.0 111.5 2,899 2,660 25,000 Electronic 1.15 67.5 6,668 6,118

0 27.8 86.0 2,391 1,650 20,000 Electronic 1.00 63.6 4,782 3,300

1 27.8 104.3 2,900 2,660 20,000 Electronic 1.00 63.6 5,799 5,320

2 27.8 109.7 3,050 2,898 20,000 Electronic 1.00 63.6 6,099 5,796

2 26.0 111.5 2,899 2,660 25,000 Electronic 1.00 59.6 5,798 5,320

0 27.8 86.0 2,391 1,650 20,000 Electronic 0.90 58.9 4,303 2,970

1 27.8 104.3 2,900 2,660 20,000 Electronic 0.90 58.9 5,219 4,788

2 27.8 109.7 3,050 2,898 20,000 Electronic 0.90 58.9 5,489 5,216

2 26.0 111.5 2,899 2,660 25,000 Electronic 0.90 54.4 5,218 4,788 * All systems use 2 lamps per ballast.5A-11 

### 5A.2.1 .5 4-foot T5 Miniature Bipin High Ou tput General Service Fluorescent Lamps
Table 5A.2.10 4-foot T5 Miniature Bipin Hig h Output 2-Lamps per Ballast Lamp-andBallast Designs in the Industrial SectorRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

0 53.8 76.0 4,089 2,885 20,000 Electronic 1.00 120.0 8,178 5,770

1 51.0 98.0 4,998 4,600 25,000 Electronic 1.00 117.0 9,996 9,200 * All systems use 2 lamps per ballast.5A-12 

### 5A.2.2 Sy stems Used by Consumers of T12 Electronic Ballasts

5A.2.2.1 4-foot Medium Bipin General Service Fluorescent Lamps
Table 5A.2.11 4-foot T8 Medium Bipin 3-Lamps per Ballast Lamp-and-Ballast Designs in the Commercial and Industrial SectorsRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.75 75.3 6,750 6,413

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.88 86.8 7,920 7,524

4 26.6 93.0 2,475 2,350 30,000 Electronic 1.18 87.7 8,762 8,319

4 26.6 93.0 2,475 2,350 30,000 Electronic 0.88 66.5 6,534 6,204

4 30.4 93.8 2,850 2,680 20,000 Electronic 0.78 72.2 6,669 6,271

4 30.4 93.8 2,850 2,680 20,000 Electronic 1.00 90.3 8,550 8,040

5 32.5 95.4 3,100 2,915 24,000 Electronic 0.71 71.7 6,603 6,209

5 32.5 95.4 3,100 2,915 24,000 Electronic 0.88 86.8 8,184 7,696

5 28.4 96.0 2,725 2,560 18,000 Electronic 1.00 84.6 8,175 7,680

5 28.4 96.0 2,725 2,560 18,000 Electronic 0.78 67.5 6,377 5,990 * All systems use 3 lamps per ballast.



### Table 5A.2.12 4-foot T12 Medium Bipin 3-Lamps per Ballast Lamp-and-Ballast Designs in the Commercial and Industrial SectorsRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

0 41.0 78.0 3,200 2,880 20,000 Electronic 0.88 107.7 8,448 7,603

0 34.0 77.9 2,650 2,300 20,000 Electronic 0.88 91.7 6,996 6,072 * All systems use 3 lamps per ballast.5A-13 

### Table 5A.2.13 4-foot T8 Medium Bipin 2-Lamp s per Ballast Lamp-and-Ballast Designs in the Residential SectorRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

4 32.5 92.3 3,000 2,850 24,000 Electronic 0.75 49.6 4,500 4,275

4 26.6 93.0 2,475 2,350 30,000 Electronic 0.78 40.5 3,861 3,666

4 30.4 93.8 2,850 2,680 20,000 Electronic 0.75 47.2 4,275 4,020

5 32.5 95.4 3,100 2,915 24,000 Electronic 0.71 46.8 4,402 4,139

5 28.4 96.0 2,725 2,560 18,000 Electronic 0.78 45.6 4,251 3,994 * All systems use 2 lamps per ballast.



### Table 5A.2.14 4-foot T12 Medium Bipin 2-Lamps per Ballast Lamp-and-Ballast Designs in the Residential SectorRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

0 41.0 76.8 3,150 2,860 15,000 Electronic 0.65 58.0 4,095 3,718 * All systems use 2 lamps per ballast.5A-14 

### 5A.2.2.2 8-foot Single Pin Slimline Ge neral Service Fluo rescent Lamps
Table 5A.2.15 8-foot T8 Single Pin Slimline 2-Lamps per Ballast Lamp-and-Ballast Designs in the Commercial and Industrial SectorsRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

4 60.1 98.2 5,900 5,428 15,000 Electronic 0.78 100.4 9,204 8,468

5 60.1 101.5 6,100 5,795 18,000 Electronic 0.88 112.8 10,736 10,199

5 60.1 101.5 6,100 5,795 18,000 Electronic 0.78 100.4 9,516 9,040

5 57.0 101.8 5,800 5,450 24,000 Electronic 0.78 102.5 9,048 8,502 * All systems use 2 lamps per ballast.



### Table 5A.2.16 8-foot T12 Single Pin Slimli ne 2-Lamps per Ballast Lamp-and-Ballast Designs in the Commercial and Industrial SectorsRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

0 75.0 85.6 6,420 5,906 12,000 Electronic 0.88 135.0 11,299 10,395

1 60.5 87.6 5,300 4,664 12,000 Electronic 0.88 110.0 9,328 8,209 * All systems use 2 lamps per ballast.5A-15 

### 5A.2.2.3 8-foot Recessed Double Contact High Output General Service Fluorescent Lamps

Table 5A.2.17 8-foot T8 Recessed Double Co ntact High Output 2-Lamps per Ballast Lamp-and-Ballast Designs in the Industrial SectorRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

4 86.0 91.9 7,900 7,100 24,000 Electronic 0.88 160.0 13,904 12,496

4 86.0 93.0 8,000 7,200 18,000 Electronic 0.88 160.0 14,080 12,672

5 86.0 95.3 8,200 7,800 18,000 Electronic 0.88 160.0 14,432 13,728

5 86.0 95.3 8,200 7,800 18,000 Electronic 0.81 151.0 13,284 12,636 * All systems use 2 lamps per ballast.



### Table 5A.2.18 8-foot T12 Recessed Double Co ntact High Output 2-Lamps per Ballast Lamp-and-Ballast Designs in the Industrial SectorRated WattageRated EfficacyInitial LightOutputMean LightOutputLifeSystem PowerRating*System InitialLight OutputSystem MeanLight OutputEfficacy LevelWlm/WlmlmhrBallast TypeBallast FactorWlmlm

0 113.0 80.1 9,050 8,145 12,000 Electronic 0.90 211.5 16,290 14,661

0 97.0 82.5 8,000 6,950 12,000 Electronic 0.90 185.6 14,400 12,510 * All systems use 2 lamps per ballast.5A-16 

### 5A.3 INCA NDESCENT REFLECTOR LAMPS

The following tables list the lam p designs used in the shipments analysis and NIA for incandescent reflector lamps (IRL). In addition to the lamp designs considered in the LCC and PBP analysis, the shipments analysis and NIA include 65W BR30 1 

### IRL that are exempt from coverage. The shipments analysis and NIA also allow users to include reflector CFL in the analysis.

Table 5A.3.1 90W PAR38 Incandescent Reflector Lamps

Wattage Initial Light Output Mean Light Output Efficacy Lamp Life EL 2 Design Option Lamp Descriptor
W lm lm lm/W hr

0 Halogen PAR38 3 90.0 1,310 1,277 14.6 2,500

1 Improved Halogen (Xenon) PAR38 85.7 1,310 1,277 15.3 2,500

1 Improved Halogen (Xenon) PAR38 90.0 1,396 1,361 15.5 2,500

2 Long Life HIR PAR38 82.5 1,310 1,277 15.9 6,000

2 Long Life HIR PAR38 90.0 1,470 1,433 16.3 6,000

2 Improved Halogen (Silver) PAR38 79.0 1,310 1,277 16.6 3,000

3 Improved Halogen (Silver) PAR38 70.0 1,260 1,229 18.0 3,000

3 HIR PAR38 100.0 2,030 1,979 20.3 3,000

4 HIR PAR38 66.0 1,310 1,277 19.8 4,000

4 Improved HIR PAR38 90.0 2,030 1,979 22.6 4,000 Improved HIR Reflector CFL 26.0 1,300 1,040 50.0 8,000

5 Reflector CFL PAR38 60.0 1,260 1,229 21.0 4,200

5 Improved HIR Plus PAR38 90.0 2,217 2,162 24.6 4,200

1 BR stands for “Bulged Reflector.”

2 EL stands for “Efficacy Level.”

3 PAR stands for “Parabolic Aluminized Reflector.”5A-17 

### Table 5A.3.2 75W PAR38 Incandescent Reflector Lamps

Wattage Initial Light Output Mean Light Output Efficacy Lamp Life EL Design Option Lamp Descriptor
W lm lm lm/W hr

0 Halogen PAR38 75.0 1,050 1,024 14.0 2,500

1 Improved Halogen (Xenon) PAR38 71.7 1,050 1,024 14.6 2,500

1 Improved Halogen (Xenon) PAR38 75.0 1,103 1,075 14.7 2,500

2 Long Life HIR PAR38 68.8 1,050 1,024 15.3 6,000

2 Long Life HIR PAR38 88.0 1,470 1,433 16.7 6,000

2 Improved Halogen (Silver) PAR38 66.0 1,050 1,024 15.9 3,000

2 Improved Halogen (Silver) PAR38 79.0 1,310 1,277 16.6 3,000

3 HIR PAR38 60.0 1,050 1,024 17.5 3,000

3 HIR PAR38 80.0 1,500 1,463 18.8 3,000

4 Improved HIR PAR38 55.0 1,050 1,024 19.1 4,000

4 Improved HIR PAR38 90.0 2,030 1,979 22.6 4,000

Reflector CFL Reflector CFL 23.0 1,200 960 52.2 8,000

5 Improved HIR Plus PAR38 51.7 1,050 1,024 20.3 4,200

5 Improved HIR Plus PAR38 83.0 2,030 1,979 24.5 4,2005A-18 

### Table 5A.3.3 50W PAR30 Incandescent Reflector Lamps

Wattage Initial Light Output Mean Light Output Efficacy Lamp Life EL Design Option Lamp Descriptor
W lm lm lm/W hr

BR30 Incandescent IRL BR30 Incandescent 65.0 620 564 9.5 2,000

0 Halogen PAR30 50.0 630 614 12.6 3,000

1 Improved Halogen (Xenon) PAR30 47.8 630 614 13.2 3,000

1 Improved Halogen (Xenon) PAR30 50.0 662 645 13.2 3,000

2 Long Life HIR PAR30 46.0 620 605 13.5 6,000

2 Long Life HIR PAR30 50.0 695 678 13.9 6,000

2 Improved Halogen (Silver) PAR30 45.0 630 614 14.0 3,000

2 Improved Halogen (Silver) PAR30 50.0 720 702 14.4 3,000

3 HIR PAR30 41.8 630 614 15.1 3,000

3 HIR PAR30 50.0 825 804 16.5 4,000

4 Improved HIR PAR30 40.0 680 663 17.0 4,000

4 Improved HIR PAR30 50.0 900 878 18.0 3,000

Reflector CFL Reflector CFL 16.0 750 600 46.9 8,000

5 Improved HIR Plus PAR30 40.0 765 746 19.1 4,200

5 Improved HIR Plus PAR30 50.0 1,014 989 20.3 4,200