Name: Rudy Sanchez

Title: General Plant Manager

Company: Floriday Power & Light Co

Sign Date: 6/22/2010

Name: Thomas K. Graham

Title: Director of Operations

Company: Air Hygiene International, Inc.

Sign Date: 5/14/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Turkey Point Energy Center, Unit #2, Information Collection Request

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Monday, February 14, 2011 Page 1 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Facility Information:

Turkey Point Energy Center

9760 SW 344th Street

Homestead FL 33035

Contact: Augie De La Vega

Phone: (305) 242-3896

Fax:

Email: augie.de.la.vega@fpl.com

Testing Company:

Air Hygiene International, Inc.

5634 S. 122nd East Ave, Suite F

Tulsa OK 74146

Contact:Thomas Graham

Phone: (918) 307-8865

Fax: (918) 307-9131

Email: tom@airhygiene.com

Air Permit Number:

0250003-011-AV

Permitted Source ID/Name:

PTP2 Foster Wheeler, Wall Fired Boiler

Permitted Maximum Process Rate:

440 MW

Max. Normal Operation Process Rate:

400 MW

Target Process Test Rate

375 MW

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Florida Power and Light Company (FPL) operates two oil fired electric utility steam generating units of Foster 

Wheeler design, designated as Units PTP1 and PTP2. The facility is located at 9760 SW 344th Street in Homestead, 

Florida. Unit PTP1 and PTP2 are of identical design and consists of two wall fired boilers and ancillary equipment 

designed to generate 440 megawatts (MW) of electricity each with rated heat inputs of 4,000 million British thermal 

units per hour (MMBtu/hr) based on high heating value (HHV). Fuel oil consumption is rated at 228,000 pounds per 

hour. Unit PTP1 and PTP2 utilize low nitrogen oxide (NOx) burner technology to control NOx emissions and 

cyclone separators to control particulate matter (PM) emissions. Emission testing will be conducted from platforms 

on the independent stacks of each unit.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 0250003 FRS #: 110000914832

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

PTP2 - D/F 236.5 0 0 0 2202 2002 4 12

PTP2 - Gases 236.5 0 0 0 2202 2002 4 1

PTP2 - Metals 236.5 0 0 0 2202 2002 4 12

PTP2 - PM 236.5 0 0 0 2202 2002 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Regulation Description Compound Limit Unit

Not applicable.

Monday, February 14, 2011 Page 2 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

PTP2 - D/F % H2O Method 1 - 4 3 480 12

PTP2 - D/F 2,3,7,8-TCDD Method 23 3 480 12

PTP2 - D/F 1,2,3,7,8-PeCDD Method 23 3 480 12

PTP2 - D/F 1,2,3,4,7,8-HxCDD Method 23 3 480 12

PTP2 - D/F 1,2,3,6,7,8-HxCDD Method 23 3 480 12

PTP2 - D/F 1,2,3,7,8,9-HxCDD Method 23 3 480 12

PTP2 - D/F 1,2,3,4,6,7,8-HpCDD Method 23 3 480 12

PTP2 - D/F OCDD Method 23 3 480 12

PTP2 - D/F 2,3,7,8-TCDF Method 23 3 480 12

PTP2 - D/F 1,2,3,7,8-PeCDF Method 23 3 480 12

PTP2 - D/F 2,3,4,7,8-PeCDF Method 23 3 480 12

PTP2 - D/F 1,2,3,4,7,8-HxCDF Method 23 3 480 12

PTP2 - D/F 1,2,3,6,7,8-HxCDF Method 23 3 480 12

PTP2 - D/F 2,3,4,6,7,8-HxCDF Method 23 3 480 12

PTP2 - D/F 1,2,3,7,8,9-HxCDF Method 23 3 480 12

PTP2 - D/F 1,2,3,4,6,7,8-HpCDF Method 23 3 480 12

PTP2 - D/F 1,2,3,4,7,8,9-HpCDF Method 23 3 480 12

PTP2 - D/F OCDF Method 23 3 480 12

PTP2 - D/F Total Dioxins Method 23 3 480 12

PTP2 - D/F Total Furans Method 23 3 480 12

PTP2 - D/F 3,3',4,4'-TCB (PCB77) Method 23 3 480 12

PTP2 - D/F 3,4,4',5-TCB (PCB81) Method 23 3 480 12

PTP2 - D/F 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 12

PTP2 - D/F 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 12

PTP2 - D/F 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 12

PTP2 - D/F 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 12

PTP2 - D/F 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 12

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

PTP2 - D/F Method 23 3 480 12

PTP2 - D/F 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 12

PTP2 - D/F 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 12

2,3,3',4,4',5,5'-HpCB 

(PCB189)

PTP2 - D/F Method 23 3 480 12

PTP2 - D/F O2 Method 3A O2 3 480 12

PTP2 - D/F Co2 Method 3A CO2 3 480 12

% H2O Method 1 - 4 3 120 1 Determined after 

initial stratification test

PTP2 - Gases

Carbon Monoxide Method 10 3 120 1 Determined after 

initial stratification test

PTP2 - Gases

Total organic compounds 

(TOC) as Propane

Method 25A 3 120 1 Determined after 

initial stratification test

PTP2 - Gases

O2 Method 3A O2 3 120 1 Determined after 

initial stratification test

PTP2 - Gases

Co2 Method 3A CO2 3 120 1 Determined after 

initial stratification test

PTP2 - Gases

Sulfur Dioxide Method 6C 3 120 1 Determined after 

initial stratification test

PTP2 - Gases

Nitrogen oxides (NOx) Method 7E 3 120 1 Determined after 

initial stratification test

PTP2 - Gases

PTP2 - Metals % H2O Method 1 - 4 3 240 12

PTP2 - Metals Selenium Method 29 3 240 12

PTP2 - Metals Manganese Method 29 3 240 12

Monday, February 14, 2011 Page 3 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

PM Run All - reduced to 2 hour runs to avoid high vacuum, did not pull required volumes
PM Run 3 - oily 

substance on Run 3 filters

PTP2 - Metals Lead Method 29 3 240 12

PTP2 - Metals Filterable Particulate Method 29 3 240 12

PTP2 - Metals Cobalt Method 29 3 240 12

PTP2 - Metals Cadmium Method 29 3 240 12

PTP2 - Metals Chromium Method 29 3 240 12

PTP2 - Metals Nickel Method 29 3 240 12

PTP2 - Metals Co2 Method 3A CO2 3 240 12

PTP2 - Metals O2 Method 3A O2 3 240 12

% H2O Method 1 - 4 3 120 12 Run times vary based 

on method calculations

PTP2 - PM

Filterable Particulate OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PTP2 - PM

Filterable PM2.5 OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PTP2 - PM

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PTP2 - PM

Organic Condensible 

Particulate

OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PTP2 - PM

Total PM2.5 OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PTP2 - PM

Total Particulate OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PTP2 - PM

O2 Method 3A O2 3 120 12 Run times vary based 

on method calculations

PTP2 - PM

Co2 Method 3A CO2 3 120 12 Run times vary based 

on method calculations

PTP2 - PM

Monday, February 14, 2011 Page 4 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Sampling / Stack Data Results Summary

Location PTP2 - D/F - Method 23

Average

Run Number PTP2-23-1 PTP2-23-2 PTP2-23-3

Test Date 3/26/2010 3/27/2010 3/30/2010

Run Start Time 1:03:00 PM 9:10:00 

AM

10:36:00 AM

Run Finish Time 10:58:00 PM 7:01:00 PM 7:05:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 405.610 388.589 377.292 390.497

Moisture Content of Stack Gas, % 8.30 8.69 8.18 8.390

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 14.51 14.67 14.7 14.627

Oxygen, % 3.42 3.37 3.31 3.367

Average Stack Gas Temperature, °F 290.00 284.67 284.50 286.390

Dry Volumetric Flow Rate, dry scfm 753,828.4 731,752.3 748,421.1 744,667.267

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,174,370.5 1,135,566.5 1,155,883.7 1,155,273.56

7

Percent Isokinetic of Sampling Rate, % 100.3 99.0 94.0 97.767

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PTP2 - Gases - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, February 14, 2011 Page 5 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location PTP2 - Gases - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location PTP2 - Gases - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, February 14, 2011 Page 6 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location PTP2 - Gases - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location PTP2 - Gases - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, February 14, 2011 Page 7 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location PTP2 - Gases - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location PTP2 - Metals - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Monday, February 14, 2011 Page 8 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location PTP2 - PM - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Monday, February 14, 2011 Page 9 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Emissions Summary

Location: PTP2 - D/F - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.00000000678 0.0000000043 0.0000000066 0.000

lb/mmBtuO2 4.05E-13 2.67E-13 4.21E-13 0.000

ng/dscm 5.90E-04 3.91E-04 6.18E-04 0.001

ng/dscm@7%O2 4.69E-04 3.10E-04 4.88E-04 0.000

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000025 0.0000000025 0.000000003 0.000

lb/mmBtuO2 1.49E-13 1.55E-13 1.91E-13 0.000

ng/dscm 2.18E-04 2.27E-04 2.81E-04 0.000

ng/dscm@7%O2 1.73E-04 1.80E-04 2.22E-04 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000027 0.0000000014 0.0000000019 0.000

lb/mmBtuO2 1.61E-13 8.70E-14 1.21E-13 0.000

ng/dscm 2.35E-04 1.27E-04 1.78E-04 0.000

ng/dscm@7%O2 1.87E-04 1.01E-04 1.41E-04 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.000000002 0.0000000016 0.0000000018 0.000

lb/mmBtuO2 1.19E-13 9.95E-14 1.15E-13 0.000

ng/dscm 1.74E-04 1.45E-04 1.69E-04 0.000

ng/dscm@7%O2 1.38E-04 1.15E-04 1.34E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000026 0.0000000008 0.0000000027 0.000

lb/mmBtuO2 1.55E-13 4.97E-14 1.72E-13 0.000

ng/dscm 2.26E-04 7.27E-05 2.53E-04 0.000

ng/dscm@7%O2 1.80E-04 5.76E-05 2.00E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.000000002 0.0000000016 0.0000000018 0.000

lb/mmBtuO2 1.19E-13 9.95E-14 1.15E-13 0.000

ng/dscm 1.74E-04 1.45E-04 1.69E-04 0.000

ng/dscm@7%O2 1.38E-04 1.15E-04 1.34E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

Monday, February 14, 2011 Page 10 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000025 0.00000000074 0.0000000025 0.000

lb/mmBtuO2 1.49E-13 4.60E-14 1.60E-13 0.000

ng/dscm 2.18E-04 6.73E-05 2.34E-04 0.000

ng/dscm@7%O2 1.73E-04 5.34E-05 1.85E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.00000000481 0.0000000016 0.0000000018 0.000

lb/mmBtuO2 2.87E-13 9.95E-14 1.15E-13 0.000

ng/dscm 4.19E-04 1.45E-04 1.69E-04 0.000

ng/dscm@7%O2 3.33E-04 1.15E-04 1.34E-04 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000028 0.00000000085 0.0000000029 0.000

lb/mmBtuO2 1.67E-13 5.28E-14 1.85E-13 0.000

ng/dscm 2.44E-04 7.73E-05 2.71E-04 0.000

ng/dscm@7%O2 1.94E-04 6.13E-05 2.14E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000023 0.0000000016 0.0000000017 0.000

lb/mmBtuO2 1.37E-13 9.95E-14 1.08E-13 0.000

ng/dscm 2.00E-04 1.45E-04 1.59E-04 0.000

ng/dscm@7%O2 1.59E-04 1.15E-04 1.26E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000017 0.0000000015 0.00000000478 0.000

lb/mmBtuO2 1.02E-13 9.32E-14 3.05E-13 0.000

ng/dscm 1.48E-04 1.36E-04 4.47E-04 0.000

ng/dscm@7%O2 1.18E-04 1.08E-04 3.53E-04 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000107 0.0000000081 0.0000000049 0.000

lb/mmBtuO2 6.39E-13 5.04E-13 3.13E-13 0.000

ng/dscm 9.32E-04 7.36E-04 4.59E-04 0.001

ng/dscm@7%O2 7.41E-04 5.84E-04 3.63E-04 0.001

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000571 0.0000000291 0.0000000274 0.000

lb/mmBtuO2 3.41E-12 1.81E-12 1.75E-12 0.000

ng/dscm 4.97E-03 2.64E-03 2.57E-03 0.003

ng/dscm@7%O2 3.95E-03 2.09E-03 2.03E-03 0.003

Monday, February 14, 2011 Page 11 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.000000856 0.000000533 0.000000373 0.000

lb/mmBtuO2 5.11E-11 3.31E-11 2.38E-11 0.000

ng/dscm 7.45E-02 4.84E-02 3.49E-02 0.053

ng/dscm@7%O2 5.92E-02 3.84E-02 2.76E-02 0.042

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.000000122 0.000000059 0.0000000434 0.000

lb/mmBtuO2 7.29E-12 3.67E-12 2.77E-12 0.000

ng/dscm 1.06E-02 5.36E-03 4.06E-03 0.007

ng/dscm@7%O2 8.43E-03 4.25E-03 3.21E-03 0.005

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000508 0.00000004 0.0000000297 0.000

lb/mmBtuO2 3.03E-12 2.49E-12 1.90E-12 0.000

ng/dscm 4.42E-03 3.64E-03 2.78E-03 0.004

ng/dscm@7%O2 3.51E-03 2.89E-03 2.20E-03 0.003

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.00000207 0.00000134 0.000000993 0.000

lb/mmBtuO2 1.24E-10 8.33E-11 6.34E-11 0.000

ng/dscm 1.80E-01 1.22E-01 9.30E-02 0.132

ng/dscm@7%O2 1.43E-01 9.67E-02 7.35E-02 0.104

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000355 0.0000000247 0.0000000167 0.000

lb/mmBtuO2 2.12E-12 1.54E-12 1.07E-12 0.000

ng/dscm 3.09E-03 2.25E-03 1.56E-03 0.002

ng/dscm@7%O2 2.46E-03 1.78E-03 1.23E-03 0.002

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000025 0.0000000027 0.0000000026 0.000

lb/mmBtuO2 1.49E-13 1.68E-13 1.66E-13 0.000

ng/dscm 2.18E-04 2.45E-04 2.43E-04 0.000

ng/dscm@7%O2 1.73E-04 1.94E-04 1.92E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000016 0.0000000014 0.0000000039 0.000

lb/mmBtuO2 9.56E-14 8.70E-14 2.49E-13 0.000

Monday, February 14, 2011 Page 12 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

ng/dscm 1.39E-04 1.27E-04 3.65E-04 0.000

ng/dscm@7%O2 1.11E-04 1.01E-04 2.88E-04 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000032 0.0000000026 0.0000000023 0.000

lb/mmBtuO2 1.91E-13 1.62E-13 1.47E-13 0.000

ng/dscm 2.79E-04 2.36E-04 2.15E-04 0.000

ng/dscm@7%O2 2.22E-04 1.87E-04 1.70E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000041 0.0000000032 0.0000000032 0.000

lb/mmBtuO2 2.45E-13 1.99E-13 2.04E-13 0.000

ng/dscm 3.57E-04 2.91E-04 3.00E-04 0.000

ng/dscm@7%O2 2.84E-04 2.31E-04 2.37E-04 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.00000000071 0.00000000069 0.00000000079 0.000

lb/mmBtuO2 4.24E-14 4.29E-14 5.04E-14 0.000

ng/dscm 6.18E-05 6.27E-05 7.40E-05 0.000

ng/dscm@7%O2 4.91E-05 4.97E-05 5.85E-05 0.000

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.000000011 0.0000000092 0.0000000032 0.000

lb/mmBtuO2 6.57E-13 5.72E-13 2.04E-13 0.000

ng/dscm 9.58E-04 8.36E-04 3.00E-04 0.001

ng/dscm@7%O2 7.62E-04 6.63E-04 2.37E-04 0.001

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.000000131 0.000000138 0.0000000603 0.000

lb/mmBtuO2 7.82E-12 8.58E-12 3.85E-12 0.000

ng/dscm 1.14E-02 1.25E-02 5.64E-03 0.010

ng/dscm@7%O2 9.07E-03 9.91E-03 4.46E-03 0.008

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.00000000561 0.00000000665 0.00000000462 0.000

lb/mmBtuO2 3.35E-13 4.13E-13 2.95E-13 0.000

ng/dscm 4.89E-04 6.04E-04 4.32E-04 0.001

ng/dscm@7%O2 3.89E-04 4.79E-04 3.41E-04 0.000

Compound: OCDD

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Monday, February 14, 2011 Page 13 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Mass_mg 0.000000015 0.000000004 0.00000000989 0.000

lb/mmBtuO2 8.96E-13 2.49E-13 6.31E-13 0.000

ng/dscm 1.31E-03 3.64E-04 9.26E-04 0.001

ng/dscm@7%O2 1.04E-03 2.89E-04 7.32E-04 0.001

Compound: OCDF

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000049 0.0000000052 0.0000000057 0.000

lb/mmBtuO2 2.93E-13 3.23E-13 3.64E-13 0.000

ng/dscm 4.27E-04 4.73E-04 5.34E-04 0.000

ng/dscm@7%O2 3.40E-04 3.75E-04 4.22E-04 0.000

Compound: Total Dioxins

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.00000003609 0.0000000173 0.00000002589 0.000

lb/mmBtuO2 2.16E-12 1.08E-12 1.65E-12 0.000

ng/dscm 3.14E-03 1.57E-03 2.42E-03 0.002

ng/dscm@7%O2 2.50E-03 1.24E-03 1.91E-03 0.002

Compound: Total Furans

Average

RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3

Mass_mg 0.0000000279 0.00000002029 0.00000003318 0.000

lb/mmBtuO2 1.67E-12 1.26E-12 2.12E-12 0.000

ng/dscm 2.43E-03 1.84E-03 3.11E-03 0.002

ng/dscm@7%O2 1.93E-03 1.46E-03 2.46E-03 0.002

Location: PTP2 - Gases - Method 10

Compound: Carbon Monoxide

Average

Run 2-CO-1 2-CO-2 2-CO-3

lb/mmBtuO2 4.33E-02 6.84E-02 9.47E-03 0.040

ppm 5.39E+01 8.62E+01 1.18E+01 50.633

ppm@7%O2 4.31E+01 6.81E+01 9.39E+00 40.197

Location: PTP2 - Gases - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 2-THC-1 2-THC-2 2-THC-3

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ppm 0.00E+00 0.00E+00 0.00E+00 0.000

ppm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Location: PTP2 - Gases - Method 6C

Compound: Sulfur Dioxide

Average

Run 2-SO2-1 2-SO2-2 2-SO2-3

lb/mmBtuO2 8.67E-01 9.40E-01 9.24E-01 0.910

ppm 4.72E+02 5.18E+02 5.05E+02 498.333

ppm@7%O2 3.77E+02 4.09E+02 4.02E+02 396.000

Monday, February 14, 2011 Page 14 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location: PTP2 - Gases - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 2-NOx-1 2-NOx-2 2-NOx-3

lb/mmBtuO2 5.60E-01 5.73E-01 6.05E-01 0.579

ppm 4.25E+02 4.40E+02 4.60E+02 441.667

ppm@7%O2 3.40E+02 3.48E+02 3.66E+02 351.333

Location: PTP2 - Metals - Method 29

Compound: Antimony

Average

RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3

Mass_mg 0.0734 0.425 0.395 0.298

Elb/hr 3.66E-02 2.10E-01 2.00E-01 0.149

lb/mmBtuO2 9.93E-06 5.36E-05 5.07E-05 0.000

mg/dscm 1.45E-02 7.87E-02 7.44E-02 0.056

mg/dscm@7%O2 1.15E-02 6.22E-02 5.88E-02 0.044

Compound: Arsenic

Average

RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3

Mass_mg 0.00352 0.0232 0.0223 0.016

Elb/hr 1.75E-03 1.15E-02 1.13E-02 0.008

lb/mmBtuO2 4.76E-07 2.93E-06 2.86E-06 0.000

mg/dscm 6.95E-04 4.30E-03 4.20E-03 0.003

mg/dscm@7%O2 5.53E-04 3.40E-03 3.32E-03 0.002

Compound: Beryllium

Average

RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3

Mass_mg 0.000202 0.00135 0.0011 0.001

Elb/hr 1.01E-04 6.68E-04 5.57E-04 0.000

lb/mmBtuO2 2.73E-08 1.70E-07 1.41E-07 0.000

mg/dscm 3.99E-05 2.50E-04 2.07E-04 0.000

mg/dscm@7%O2 3.17E-05 1.98E-04 1.64E-04 0.000

Compound: Cadmium

Average

RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3

Mass_mg 0.000158 0.000894 0.000812 0.001

Elb/hr 7.88E-05 4.43E-04 4.11E-04 0.000

lb/mmBtuO2 2.14E-08 1.13E-07 1.04E-07 0.000

mg/dscm 3.12E-05 1.66E-04 1.53E-04 0.000

mg/dscm@7%O2 2.48E-05 1.31E-04 1.21E-04 0.000

Compound: Chromium

Average

RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3

Mass_mg 0.0107 0.0444 0.044 0.033

Elb/hr 5.33E-03 2.20E-02 2.23E-02 0.017

lb/mmBtuO2 1.45E-06 5.60E-06 5.65E-06 0.000

mg/dscm 2.11E-03 8.22E-03 8.29E-03 0.006

Monday, February 14, 2011 Page 15 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

mg/dscm@7%O2 1.68E-03 6.50E-03 6.55E-03 0.005

Compound: Cobalt

Average

RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3

Mass_mg 0.0398 0.224 0.228 0.164

Elb/hr 1.98E-02 1.11E-01 1.16E-01 0.082

lb/mmBtuO2 5.39E-06 2.83E-05 2.93E-05 0.000

mg/dscm 7.85E-03 4.15E-02 4.30E-02 0.031

mg/dscm@7%O2 6.24E-03 3.28E-02 3.40E-02 0.024

Compound: Filterable Particulate

Average

RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3

Mass_mg 35.5 239 228.6 167.700

Elb/hr 1.77E+01 1.18E+02 1.16E+02 83.900

lb/mmBtuO2 4.80E-03 3.02E-02 2.94E-02 0.021

mg/dscm 7.01E+00 4.43E+01 4.31E+01 31.470

mg/dscm@7%O2 5.57E+00 3.50E+01 3.41E+01 24.890

Compound: Lead

Average

RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3

Mass_mg 0.0177 0.0587 0.0561 0.044

Elb/hr 8.82E-03 2.91E-02 2.84E-02 0.022

lb/mmBtuO2 2.40E-06 7.41E-06 7.21E-06 0.000

mg/dscm 3.49E-03 1.09E-02 1.06E-02 0.008

mg/dscm@7%O2 2.78E-03 8.61E-03 8.38E-03 0.007

Compound: Manganese

Average

RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3

Mass_mg 0.0386 0.217 0.223 0.160

Elb/hr 1.92E-02 1.07E-01 1.13E-01 0.080

lb/mmBtuO2 5.22E-06 2.74E-05 2.86E-05 0.000

mg/dscm 7.62E-03 4.02E-02 4.20E-02 0.030

mg/dscm@7%O2 6.06E-03 3.18E-02 3.32E-02 0.024

Compound: Nickel

Average

RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3

Mass_mg 0.766 4.66 4.6 3.342

Elb/hr 3.82E-01 2.31E+00 2.33E+00 1.674

lb/mmBtuO2 1.04E-04 5.88E-04 5.91E-04 0.000

mg/dscm 1.51E-01 8.63E-01 8.67E-01 0.627

mg/dscm@7%O2 1.20E-01 6.82E-01 6.85E-01 0.496

Compound: Selenium

Average

RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3

Mass_mg 0.002 0.0194 0.0254 0.016

Elb/hr 9.97E-04 9.60E-03 1.29E-02 0.008

lb/mmBtuO2 2.71E-07 2.45E-06 3.26E-06 0.000

mg/dscm 3.95E-04 3.59E-03 4.79E-03 0.003

Monday, February 14, 2011 Page 16 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Process Run Data

mg/dscm@7%O2 3.14E-04 2.84E-03 3.79E-03 0.002

Location: PTP2 - PM - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber PTP2-27/28-2 PTP2-27/28-3 PTP2-27/28-1

Mass_mg 54.167 42.167 48.217 48.184

lb/mmBtuO2 2.59E-02 2.13E-02 2.55E-02 0.024

Compound: Filterable PM2.5

Average

RunNumber PTP2-27/28-1 PTP2-27/28-2 PTP2-27/28-3

Mass_mg 35.833 42.508 32.858 37.066

lb/mmBtuO2 1.89E-02 2.04E-02 1.66E-02 0.019

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber PTP2-27/28-1 PTP2-27/28-2 PTP2-27/28-3

Mass_mg 2.826 0.693 24.764 9.428

lb/mmBtuO2 1.49E-03 3.32E-04 1.25E-02 0.005

Compound: Organic Condensible Particulate

Average

RunNumber PTP2-27/28-1 PTP2-27/28-2 PTP2-27/28-3

Mass_mg 0.467 1.775 25.208 9.150

lb/mmBtuO2 2.47E-04 8.50E-04 1.27E-02 0.005

Compound: Total Particulate

Average

RunNumber PTP2-27/28-1 PTP2-27/28-2 PTP2-27/28-3

Mass_mg 51.509 56.635 92.139 66.761

lb/mmBtuO2 2.72E-02 2.71E-02 4.65E-02 0.034

Compound: Total PM2.5

Average

RunNumber PTP2-27/28-1 PTP2-27/28-2 PTP2-27/28-3

Mass_mg 39.126 44.976 82.83 55.644

lb/mmBtuO2 2.07E-02 2.15E-02 4.18E-02 0.028

Monday, February 14, 2011 Page 17 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Residual Oil (No. 6) Burned 28349 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/26/2010; 

Start - 12:45; 

End - 14:45

0

10 Residual Oil (No. 6) Burned 28346 gal/hr Method 027/028; 

Run PM-1; Date - 

3/25/2010; Start - 

17:19; End - 20:53

0

11 Residual Oil (No. 6) Burned 28375 gal/hr Method 027/028; 

Run PM-2; Date - 

3/27/2010; Start - 

09:12; End - 11:55

0

12 Residual Oil (No. 6) Burned 28448 gal/hr Method 027/028; 

Run PM-3; Date - 

3/30/2010; Start - 

21:44; End - 23:57

0

2 Residual Oil (No. 6) Burned 28349 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/26/2010; 

Start - 15:05; 

End - 17:05

0

3 Residual Oil (No. 6) Burned 28349 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/26/2010; 

Start - 17:25; 

End - 19:24

0

4 Residual Oil (No. 6) Burned 28346 gal/hr Method 23; Run 

D/F-1; Date - 

3/26/2010; Start - 

13:03; End - 22:58

0

5 Residual Oil (No. 6) Burned 28375 gal/hr Method 23; Run 

D/F-2; Date - 

3/27/2010; Start - 

09:10; End - 19:01

0

6 Residual Oil (No. 6) Burned 28448 gal/hr Method 23; Run 

D/F-3; Date - 

3/30/2010; Start - 

10:36; End - 19:05

0

7 Residual Oil (No. 6) Burned 28346 gal/hr Method 29; Run 

M-1; Date - 

3/26/2010; Start - 

15:03; End - 19:38

0

Monday, February 14, 2011 Page 18 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

8 Residual Oil (No. 6) Burned 28448 gal/hr Method 29; Run 

M-2; Date - 

3/30/2010; Start - 

09:17; End - 13:38

0

9 Residual Oil (No. 6) Burned 28448 gal/hr Method 29; Run 

M-3; Date - 

3/30/2010; Start - 

14:17; End - 18:37

0

1 Average Heat Input 3537 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/26/2010; 

Start - 12:45; 

End - 14:45

0

10 Average Heat Input 3537 MMBtu/hr Method 027/028; 

Run PM-1; Date - 

3/25/2010; Start - 

17:19; End - 20:53

0

11 Average Heat Input 3541 MMBtu/hr Method 027/028; 

Run PM-2; Date - 

3/27/2010; Start - 

09:12; End - 11:55

0

12 Average Heat Input 3550 MMBtu/hr Method 027/028; 

Run PM-3; Date - 

3/30/2010; Start - 

21:44; End - 23:57

0

2 Average Heat Input 3537 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/26/2010; 

Start - 15:05; 

End - 17:05

0

3 Average Heat Input 3537 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/26/2010; 

Start - 17:25; 

End - 19:24

0

4 Average Heat Input 3537 MMBtu/hr Method 23; Run 

D/F-1; Date - 

3/26/2010; Start - 

13:03; End - 22:58

0

5 Average Heat Input 3541 MMBtu/hr Method 23; Run 

D/F-2; Date - 

3/27/2010; Start - 

09:10; End - 19:01

0

6 Average Heat Input 3550 MMBtu/hr Method 23; Run 

D/F-3; Date - 

3/30/2010; Start - 

10:36; End - 19:05

0

Monday, February 14, 2011 Page 19 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

7 Average Heat Input 3537 MMBtu/hr Method 29; Run 

M-1; Date - 

3/26/2010; Start - 

15:03; End - 19:38

0

8 Average Heat Input 3550 MMBtu/hr Method 29; Run 

M-2; Date - 

3/30/2010; Start - 

09:17; End - 13:38

0

9 Average Heat Input 3550 MMBtu/hr Method 29; Run 

M-3; Date - 

3/30/2010; Start - 

14:17; End - 18:37

0

1 Steam Output 2586 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/26/2010; 

Start - 12:45; 

End - 14:45

0

10 Steam Output 2574 1000 lb Method 027/028; 

Run PM-1; Date - 

3/25/2010; Start - 

17:19; End - 20:53

0

11 Steam Output 2571 1000 lb Method 027/028; 

Run PM-2; Date - 

3/27/2010; Start - 

09:12; End - 11:55

0

12 Steam Output 2582 1000 lb Method 027/028; 

Run PM-3; Date - 

3/30/2010; Start - 

21:44; End - 23:57

0

2 Steam Output 2586 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/26/2010; 

Start - 15:05; 

End - 17:05

0

3 Steam Output 2586 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/26/2010; 

Start - 17:25; 

End - 19:24

0

4 Steam Output 2581 1000 lb Method 23; Run 

D/F-1; Date - 

3/26/2010; Start - 

13:03; End - 22:58

0

5 Steam Output 2576 1000 lb Method 23; Run 

D/F-2; Date - 

3/27/2010; Start - 

09:10; End - 19:01

0

Monday, February 14, 2011 Page 20 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

6 Steam Output 2576 1000 lb Method 23; Run 

D/F-3; Date - 

3/30/2010; Start - 

10:36; End - 19:05

0

7 Steam Output 2586 1000 lb Method 29; Run 

M-1; Date - 

3/26/2010; Start - 

15:03; End - 19:38

0

8 Steam Output 2575 1000 lb Method 29; Run 

M-2; Date - 

3/30/2010; Start - 

09:17; End - 13:38

0

9 Steam Output 2577 1000 lb Method 29; Run 

M-3; Date - 

3/30/2010; Start - 

14:17; End - 18:37

0

1 Unit Gross Electrical Output 392 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/26/2010; 

Start - 12:45; 

End - 14:45

0

10 Unit Gross Electrical Output 392 MWg Method 027/028; 

Run PM-1; Date - 

3/25/2010; Start - 

17:19; End - 20:53

0

11 Unit Gross Electrical Output 390 MWg Method 027/028; 

Run PM-2; Date - 

3/27/2010; Start - 

09:12; End - 11:55

0

12 Unit Gross Electrical Output 392 MWg Method 027/028; 

Run PM-3; Date - 

3/30/2010; Start - 

21:44; End - 23:57

0

2 Unit Gross Electrical Output 392 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/26/2010; 

Start - 15:05; 

End - 17:05

0

3 Unit Gross Electrical Output 392 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/26/2010; 

Start - 17:25; 

End - 19:24

0

4 Unit Gross Electrical Output 391 MWg Method 23; Run 

D/F-1; Date - 

3/26/2010; Start - 

13:03; End - 22:58

0

Monday, February 14, 2011 Page 21 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

5 Unit Gross Electrical Output 391 MWg Method 23; Run 

D/F-2; Date - 

3/27/2010; Start - 

09:10; End - 19:01

0

6 Unit Gross Electrical Output 391 MWg Method 23; Run 

D/F-3; Date - 

3/30/2010; Start - 

10:36; End - 19:05

0

7 Unit Gross Electrical Output 392 MWg Method 29; Run 

M-1; Date - 

3/26/2010; Start - 

15:03; End - 19:38

0

8 Unit Gross Electrical Output 392 MWg Method 29; Run 

M-2; Date - 

3/30/2010; Start - 

09:17; End - 13:38

0

9 Unit Gross Electrical Output 392 MWg Method 29; Run 

M-3; Date - 

3/30/2010; Start - 

14:17; End - 18:37

0

1 Unit Net Electric Generation 372 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/26/2010; 

Start - 12:45; 

End - 14:45

0

10 Unit Net Electric Generation 372 MWn Method 027/028; 

Run PM-1; Date - 

3/25/2010; Start - 

17:19; End - 20:53

0

11 Unit Net Electric Generation 370 MWn Method 027/028; 

Run PM-2; Date - 

3/27/2010; Start - 

09:12; End - 11:55

0

12 Unit Net Electric Generation 372 MWn Method 027/028; 

Run PM-3; Date - 

3/30/2010; Start - 

21:44; End - 23:57

0

2 Unit Net Electric Generation 372 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/26/2010; 

Start - 15:05; 

End - 17:05

0

3 Unit Net Electric Generation 372 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/26/2010; 

Start - 17:25; 

End - 19:24

0

Monday, February 14, 2011 Page 22 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

APCD Run Data

Process Lab Run Data

4 Unit Net Electric Generation 371 MWn Method 23; Run 

D/F-1; Date - 

3/26/2010; Start - 

13:03; End - 22:58

0

5 Unit Net Electric Generation 371 MWn Method 23; Run 

D/F-2; Date - 

3/27/2010; Start - 

09:10; End - 19:01

0

6 Unit Net Electric Generation 372 MWn Method 23; Run 

D/F-3; Date - 

3/30/2010; Start - 

10:36; End - 19:05

0

7 Unit Net Electric Generation 372 MWn Method 29; Run 

M-1; Date - 

3/26/2010; Start - 

15:03; End - 19:38

0

8 Unit Net Electric Generation 372 MWn Method 29; Run 

M-2; Date - 

3/30/2010; Start - 

09:17; End - 13:38

0

9 Unit Net Electric Generation 372 MWn Method 29; Run 

M-3; Date - 

3/30/2010; Start - 

14:17; End - 18:37

0

Run Name Value UOM Comments

Target

Value

1 LOW NOX BURNERS 395 NOx Emissions 0

2 LOW NOX BURNERS 403 NOx Emissions 0

3 LOW NOX BURNERS 423 NOx Emissions 0

1 CYCLONE SEPARATORS 4.7 Opacity 0

2 CYCLONE SEPARATORS 4.7 Opacity 0

3 CYCLONE SEPARATORS 4.9 Opacity 0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 18300 Btu/lb

1 Fuel Moisture 0.602 %

1 Fuel Mercury Content 0.005 mg/kg

1 Fuel Chlorine Content 110 mg/kg

1 Fuel Fluorine Content 70 mg/kg

1 Fuel Antimony Content 1.8 mg/kg

1 Fuel Arsenic Content 0.078 mg/kg

1 Fuel Beryllium Content 0.008 mg/kg

Monday, February 14, 2011 Page 23 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

1 Fuel Cadmium Content 0.011 mg/kg

1 Fuel Chromium Content 0.15 mg/kg

1 Fuel Cobalt Content 0.79 mg/kg

1 Fuel Lead Content 0.42 mg/kg

1 Fuel Manganese Content 0.7 mg/kg

1 Fuel Nickel Content 19.2 mg/kg

1 Fuel Selenium Content 0.03 mg/kg

1 Fuel Sulfur Content 8650 mg/kg

1 Fuel Proximate Analysis (Carbon) 88.2 %

1 Fuel Proximate Analysis (Hydrogen) 10.25 %

1 Fuel Proximate Analysis (Nitrogen) 0.5 %

1 Fuel Proximate Analysis (Oxygen) 0.5 %

1 Fuel Proximate Analysis (Sulfur) 0.97 %

2 Fuel Higher Heating Value 18300 Btu/lb

2 Fuel Moisture 1.12 %

2 Fuel Mercury Content 0.007 mg/kg

2 Fuel Chlorine Content 120 mg/kg

2 Fuel Fluorine Content 78 mg/kg

2 Fuel Antimony Content 1.8 mg/kg

2 Fuel Arsenic Content 0.094 mg/kg

2 Fuel Beryllium Content 0.008 mg/kg

2 Fuel Cadmium Content 0.011 mg/kg

2 Fuel Chromium Content 0.16 mg/kg

2 Fuel Cobalt Content 0.82 mg/kg

2 Fuel Lead Content 0.42 mg/kg

2 Fuel Manganese Content 0.8 mg/kg

2 Fuel Nickel Content 20.3 mg/kg

2 Fuel Selenium Content 0.03 mg/kg

2 Fuel Sulfur Content 8610 mg/kg

2 Fuel Proximate Analysis (Carbon) 88.1 %

2 Fuel Proximate Analysis (Hydrogen) 10.32 %

2 Fuel Proximate Analysis (Nitrogen) 0.5 %

2 Fuel Proximate Analysis (Oxygen) 0.53 %

2 Fuel Proximate Analysis (Sulfur) 0.977 %

3 Fuel Higher Heating Value 18300 Btu/lb

3 Fuel Moisture 0.678 %

3 Fuel Mercury Content 0.010 mg/kg

3 Fuel Chlorine Content 110 mg/kg

3 Fuel Fluorine Content 74 mg/kg

3 Fuel Antimony Content 1.8 mg/kg

3 Fuel Arsenic Content 0.11 mg/kg

3 Fuel Beryllium Content 0.008 mg/kg

3 Fuel Cadmium Content 0.003 mg/kg

Monday, February 14, 2011 Page 24 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

3 Fuel Chromium Content 0.18 mg/kg

3 Fuel Cobalt Content 0.82 mg/kg

3 Fuel Lead Content 0.43 mg/kg

3 Fuel Manganese Content 0.8 mg/kg

3 Fuel Nickel Content 19.7 mg/kg

3 Fuel Selenium Content 0.03 mg/kg

3 Fuel Sulfur Content 9170 mg/kg

3 Fuel Proximate Analysis (Carbon) 87.49 %

3 Fuel Proximate Analysis (Hydrogen) 10.11 %

3 Fuel Proximate Analysis (Nitrogen) 0.53 %

3 Fuel Proximate Analysis (Oxygen) 0.53 %

3 Fuel Proximate Analysis (Sulfur) 0.983 %

Monday, February 14, 2011 Page 25 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Sampling / Stack Data Results Detail

Location PTP2 - D/F - Method 23

Average

Run Number PTP2-23-1 PTP2-23-2 PTP2-23-3

Test Date 3/26/2010 3/27/2010 3/30/2010

Run Start Time 1:03:00 PM 9:10:00 AM 10:36:00 AM

Run Finish Time 10:58:00 PM 7:01:00 PM 7:05:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.25 0.25 0.25 0.250

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.987 0.987 0.987 0.987

Barometric Pressure, inches of Mercury 29.68 29.71 29.68 29.690

Average Orifice Meter Differential, inches H2O 2.62 2.36 2.44 2.473

Dry Gas Meter Volume Sampled, cubic feet 422.260 401.780 390.110 404.717

Average Dry Gas Meter Temperature, °F 81.67 78.17 77.75 79.197

Dry Gas Meter Volume Sampled, dscf 405.610 388.589 377.292 390.497

Total Moisture Liquid collected, g 780.4 786.1 714 760.167

Volume of Water Vapor, standard cubic feet 36.73 37.00 33.61 35.780

Moisture Content of Stack Gas, % 8.30 8.69 8.18 8.390

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.917 0.9131 0.9182 0.916

Carbon Dioxide, % 14.51 14.67 14.7 14.627

Oxygen, % 3.42 3.37 3.31 3.367

Carbon Monoxide & Nitrogen, % 82.07 81.96 81.99 82.007

Fuel Factor 1.20 1.19 1.20

Dry Molecular Weight, lb/lb-Mole 30.46 30.48 30.48 30.473

Wet Molecular weight, lb/lb-Mole 29.43 29.40 29.46 29.430

Flue Gas Static Pressure, inches of H2O 1 1 1 1.000

Absolute Flue Gas Pressure, inches of Mercury 29.75 29.78 29.75 29.760

Average Stack Gas Temperature, °F 290.00 284.67 284.50 286.390

Average Velocity Head, inches of H2O 0.9319452576

11234

0.877443517

30358

0.910452885

68522

0.907

Average Stack Gas Velocity, feet/second 64.16 62.04 63.15 63.117

Stack Cross-Sectional Area, square feet 305.063 305.063 305.063 305.063

Dry Volumetric Flow Rate, dry scfm 753,828.4 731,752.3 748,421.1 744,667.267

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,174,370.5 1,135,566.5 1,155,883.7 1,155,273.5

67

Percent Isokinetic of Sampling Rate, % 100.3 99.0 94.0 97.767

Percent Excess Air, % 18.7 18.4 18.1 18.400

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 236.5 236.5 236.5

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, February 14, 2011 Page 26 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location PTP2 - Gases - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 14, 2011 Page 27 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location PTP2 - Gases - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 14, 2011 Page 28 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location PTP2 - Gases - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 14, 2011 Page 29 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location PTP2 - Gases - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 14, 2011 Page 30 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location PTP2 - Gases - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 14, 2011 Page 31 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location PTP2 - Gases - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 14, 2011 Page 32 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location PTP2 - Metals - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 14, 2011 Page 33 of 34
Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location PTP2 - PM - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 14, 2011 Page 34 of 34