### Name: Rudy Sanchez

Title: General Plant Manager Company: Floriday Power & Light Co Sign Date: 6/22/2010 Name: Thomas K. Graham Title: Director of Operations Company: Air Hygiene International, Inc. Sign Date: 5/14/2010 Permitted Facility Representative / Date Testing Company Representative / Date



## Turkey Point Energy Center, Unit #2, Information Collection Request Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Monday, February 14, 2011 Page 1 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 Facility Information: Turkey Point Energy Center
9760 SW 344th Street

Homestead FL 33035 Contact: Augie De La Vega Phone: (305) 242-3896 Fax: Email: augie.de.la.vega@fpl.com Testing Company: Air Hygiene International, Inc. 5634 S. 122nd East Ave, Suite F

Tulsa OK 74146 Contact: Thomas Graham Phone: (918) 307-8865 Fax: (918) 307-9131 Email: tom@airhygiene.com

Air Permit Number: 0250003-011-AV Permitted Source ID/Name: Foster Wheeler, Wall Fired Boiler PTP2 Permitted Maximum Process Rate: 440 MW Max. Normal Operation Process Rate: 400 MW Target Process Test Rate 375 MW

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Florida Power and Light Company (FPL) operates two oil fired electric utility steam generating units of Foster Wheeler design, designated as Units PTP1 and PTP2. The facility is located at 9760 SW 344th Street in Homestead, Florida. Unit PTP1 and PTP2 are of identical design and consists of two wall fired boilers and ancillary equipment designed to generate 440 megawatts (MW) of electricity each with rated heat inputs of 4,000 million British thermal units per hour (MMBtu/hr) based on high heating value (HHV). Fuel oil consumption is rated at 228,000 pounds per hour. Unit PTP1 and PTP2 utilize low nitrogen oxide (NOx) burner technology to control NOx emissions and cyclone separators to control particulate matter (PM) emissions. Emission testing will be conducted from platforms on the independent stacks of each unit. Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information: AFS #: 0250003 FRS #: 110000914832

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: Normal Firing

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width PTP2 - D/F 236.5 2202 2002 4 0 12 0 0 PTP2 - Gases 236.5 2202 2002 4 0 1 0 0 PTP2 - Metals 236.5 2202 2002 4 0 12 0 0 PTP2 - PM 236.5 2202 2002 4 0 12 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location Regulation Description Compound Limit Unit Not applicable.



### Monday, February 14, 2011 Page 2 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location % H2O Method 1 - 4 3 480 12 PTP2 - D/F 2,3,7,8-TCDD Method 23 3 480 12 PTP2 - D/F 1,2,3,7,8-PeCDD Method 23 3 480 12 PTP2 - D/F 1,2,3,4,7,8-HxCDD Method 23 3 480 12 PTP2 - D/F 1,2,3,6,7,8-HxCDD Method 23 3 480 12 PTP2 - D/F 1,2,3,7,8,9-HxCDD Method 23 3 480 12 PTP2 - D/F 1,2,3,4,6,7,8-HpCDD Method 23 3 480 12 PTP2 - D/F OCDD Method 23 3 480 12 PTP2 - D/F 2,3,7,8-TCDF Method 23 3 480 12 PTP2 - D/F 1,2,3,7,8-PeCDF Method 23 3 480 12 PTP2 - D/F 2,3,4,7,8-PeCDF Method 23 3 480 12 PTP2 - D/F 1,2,3,4,7,8-HxCDF Method 23 3 480 12 PTP2 - D/F 1,2,3,6,7,8-HxCDF Method 23 3 480 12 PTP2 - D/F 2,3,4,6,7,8-HxCDF Method 23 3 480 12 PTP2 - D/F 1,2,3,7,8,9-HxCDF Method 23 3 480 12 PTP2 - D/F 1,2,3,4,6,7,8-HpCDF Method 23 3 480 12 PTP2 - D/F 1,2,3,4,7,8,9-HpCDF Method 23 3 480 12 PTP2 - D/F OCDF Method 23 3 480 12 PTP2 - D/F Total Dioxins Method 23 3 480 12 PTP2 - D/F Total Furans Method 23 3 480 12 PTP2 - D/F 3,3',4,4'-TCB (PCB77) Method 23 3 480 12 PTP2 - D/F 3,4,4',5-TCB (PCB81) Method 23 3 480 12 PTP2 - D/F 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 12 PTP2 - D/F 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 12 PTP2 - D/F 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 12 PTP2 - D/F 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 12 PTP2 - D/F 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 12 PTP2 - D/F 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 480 12 PTP2 - D/F

2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 12 PTP2 - D/F 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 12 PTP2 - D/F 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 480 12 PTP2 - D/F

O2 Method 3A O2 3 480 12 PTP2 - D/F Co2 Method 3A CO2 3 480 12 PTP2 - D/F % H2O Method 1 - 4 3 120 1 Determined after initial stratification test PTP2 - Gases

Carbon Monoxide Method 10 3 120 1 Determined after initial stratification test PTP2 - Gases
Total organic compounds

(TOC) as Propane Method 25A 3 120 1 Determined after initial stratification test PTP2 - Gases

O2 Method 3A O2 3 120 1 Determined after initial stratification test PTP2 - Gases

Co2 Method 3A CO2 3 120 1 Determined after initial stratification test PTP2 - Gases

Sulfur Dioxide Method 6C 3 120 1 Determined after initial stratification test PTP2 - Gases
Nitrogen oxides (NOx) Method 7E 3 120 1 Determined after initial stratification test PTP2 - Gases

% H2O Method 1 - 4 3 240 12 PTP2 - Metals Selenium Method 29 3 240 12 PTP2 - Metals Manganese Method 29 3 240 12 PTP2 - Metals


### Monday, February 14, 2011 Page 3 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. PM Run All - reduced to 2 hour runs to avoid high vacuum, did not pull required volumes
PM Run 3 - oily substance on Run 3 filters

Lead Method 29 3 240 12 PTP2 - Metals Filterable Particulate Method 29 3 240 12 PTP2 - Metals Cobalt Method 29 3 240 12 PTP2 - Metals Cadmium Method 29 3 240 12 PTP2 - Metals Chromium Method 29 3 240 12 PTP2 - Metals Nickel Method 29 3 240 12 PTP2 - Metals Co2 Method 3A CO2 3 240 12 PTP2 - Metals O2 Method 3A O2 3 240 12 PTP2 - Metals % H2O Method 1 - 4 3 120 12 Run times vary based on method calculations PTP2 - PM

Filterable Particulate OTM - 27/28 3 120 12 Run times vary based on method calculations PTP2 - PM

Filterable PM2.5 OTM - 27/28 3 120 12 Run times vary based on method calculations PTP2 - PM
Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 120 12 Run times vary based on method calculations PTP2 - PM
Organic Condensible

Particulate OTM - 27/28 3 120 12 Run times vary based on method calculations PTP2 - PM

Total PM2.5 OTM - 27/28 3 120 12 Run times vary based on method calculations PTP2 - PM

Total Particulate OTM - 27/28 3 120 12 Run times vary based on method calculations PTP2 - PM

O2 Method 3A O2 3 120 12 Run times vary based on method calculations PTP2 - PM

Co2 Method 3A CO2 3 120 12 Run times vary based on method calculations PTP2 - PM



### Monday, February 14, 2011 Page 4 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 Sampling / Stack Data Results Summary



### Location PTP2 - D/F - Method 23 Average Run Number PTP2-23-1 PTP2-23-2 PTP2-23-3
Test Date 3/26/2010 3/27/2010 3/30/2010 Run Start Time 1:03:00 PM 9:10:00 AM 10:36:00 AM

Run Finish Time 10:58:00 PM 7:01:00 PM 7:05:00 PM Net Run Time, minutes 480 480 480 Dry Gas Meter Volume Sampled, dscf 405.610 388.589 377.292 390.497 Moisture Content of Stack Gas, % 8.30 8.69 8.18 8.390 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 14.51 14.67 14.7 14.627 Oxygen, % 3.42 3.37 3.31 3.367 Average Stack Gas Temperature, °F 290.00 284.67 284.50 286.390 Dry Volumetric Flow Rate, dry scfm 753,828.4 731,752.3 748,421.1 744,667.267 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,174,370.5 1,135,566.5 1,155,883.7 1,155,273.56 7 Percent Isokinetic of Sampling Rate, % 100.3 99.0 94.0 97.767 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Location PTP2 - Gases - Method 10 Average Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Monday, February 14, 2011 Page 5 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
Location PTP2 - Gases - Method 25A Average Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location PTP2 - Gases - Method 3A CO2 Average Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Monday, February 14, 2011 Page 6 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
Location PTP2 - Gases - Method 3A O2 Average Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location PTP2 - Gases - Method 6C Average Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Monday, February 14, 2011 Page 7 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
Location PTP2 - Gases - Method 7E Average Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location PTP2 - Metals - Method 29 Average Run Number
Test Date Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Monday, February 14, 2011 Page 8 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
Location PTP2 - PM - OTM - 27/28 Average Run Number
Test Date Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Monday, February 14, 2011 Page 9 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 Emissions Summary



### Location: PTP2 - D/F - Method 23 Compound: 1,2,3,4,6,7,8-HpCDD Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.00000000678 0.0000000043 0.0000000066 0.000 lb/mmBtuO2 4.05E-13 2.67E-13 4.21E-13 0.000 ng/dscm 5.90E-04 3.91E-04 6.18E-04 0.001 ng/dscm@7%O2 4.69E-04 3.10E-04 4.88E-04 0.000 

### Compound: 1,2,3,4,6,7,8-HpCDF Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000025 0.0000000025 0.000000003 0.000 lb/mmBtuO2 1.49E-13 1.55E-13 1.91E-13 0.000 ng/dscm 2.18E-04 2.27E-04 2.81E-04 0.000 ng/dscm@7%O2 1.73E-04 1.80E-04 2.22E-04 0.000 

### Compound: 1,2,3,4,7,8,9-HpCDF Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000027 0.0000000014 0.0000000019 0.000 lb/mmBtuO2 1.61E-13 8.70E-14 1.21E-13 0.000 ng/dscm 2.35E-04 1.27E-04 1.78E-04 0.000 ng/dscm@7%O2 1.87E-04 1.01E-04 1.41E-04 0.000 

### Compound: 1,2,3,4,7,8-HxCDD Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.000000002 0.0000000016 0.0000000018 0.000 lb/mmBtuO2 1.19E-13 9.95E-14 1.15E-13 0.000 ng/dscm 1.74E-04 1.45E-04 1.69E-04 0.000 ng/dscm@7%O2 1.38E-04 1.15E-04 1.34E-04 0.000 

### Compound: 1,2,3,4,7,8-HxCDF Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000026 0.0000000008 0.0000000027 0.000 lb/mmBtuO2 1.55E-13 4.97E-14 1.72E-13 0.000 ng/dscm 2.26E-04 7.27E-05 2.53E-04 0.000 ng/dscm@7%O2 1.80E-04 5.76E-05 2.00E-04 0.000 

### Compound: 1,2,3,6,7,8-HxCDD Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.000000002 0.0000000016 0.0000000018 0.000 lb/mmBtuO2 1.19E-13 9.95E-14 1.15E-13 0.000 ng/dscm 1.74E-04 1.45E-04 1.69E-04 0.000 ng/dscm@7%O2 1.38E-04 1.15E-04 1.34E-04 0.000 

### Compound: 1,2,3,6,7,8-HxCDF Average



### Monday, February 14, 2011 Page 10 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000025 0.00000000074 0.0000000025 0.000 lb/mmBtuO2 1.49E-13 4.60E-14 1.60E-13 0.000 ng/dscm 2.18E-04 6.73E-05 2.34E-04 0.000 ng/dscm@7%O2 1.73E-04 5.34E-05 1.85E-04 0.000 

### Compound: 1,2,3,7,8,9-HxCDD Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.00000000481 0.0000000016 0.0000000018 0.000 lb/mmBtuO2 2.87E-13 9.95E-14 1.15E-13 0.000 ng/dscm 4.19E-04 1.45E-04 1.69E-04 0.000 ng/dscm@7%O2 3.33E-04 1.15E-04 1.34E-04 0.000 

### Compound: 1,2,3,7,8,9-HxCDF Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000028 0.00000000085 0.0000000029 0.000 lb/mmBtuO2 1.67E-13 5.28E-14 1.85E-13 0.000 ng/dscm 2.44E-04 7.73E-05 2.71E-04 0.000 ng/dscm@7%O2 1.94E-04 6.13E-05 2.14E-04 0.000 

### Compound: 1,2,3,7,8-PeCDD Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000023 0.0000000016 0.0000000017 0.000 lb/mmBtuO2 1.37E-13 9.95E-14 1.08E-13 0.000 ng/dscm 2.00E-04 1.45E-04 1.59E-04 0.000 ng/dscm@7%O2 1.59E-04 1.15E-04 1.26E-04 0.000 

### Compound: 1,2,3,7,8-PeCDF Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000017 0.0000000015 0.00000000478 0.000 lb/mmBtuO2 1.02E-13 9.32E-14 3.05E-13 0.000 ng/dscm 1.48E-04 1.36E-04 4.47E-04 0.000 ng/dscm@7%O2 1.18E-04 1.08E-04 3.53E-04 0.000 

### Compound: 2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000107 0.0000000081 0.0000000049 0.000 lb/mmBtuO2 6.39E-13 5.04E-13 3.13E-13 0.000 ng/dscm 9.32E-04 7.36E-04 4.59E-04 0.001 ng/dscm@7%O2 7.41E-04 5.84E-04 3.63E-04 0.001 

### Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000571 0.0000000291 0.0000000274 0.000 lb/mmBtuO2 3.41E-12 1.81E-12 1.75E-12 0.000 ng/dscm 4.97E-03 2.64E-03 2.57E-03 0.003 ng/dscm@7%O2 3.95E-03 2.09E-03 2.03E-03 0.003



### Monday, February 14, 2011 Page 11 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 Compound: 2,3,3',4,4'-PeCB (PCB105) Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.000000856 0.000000533 0.000000373 0.000 lb/mmBtuO2 5.11E-11 3.31E-11 2.38E-11 0.000 ng/dscm 7.45E-02 4.84E-02 3.49E-02 0.053 ng/dscm@7%O2 5.92E-02 3.84E-02 2.76E-02 0.042 

### Compound: 2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.000000122 0.000000059 0.0000000434 0.000 lb/mmBtuO2 7.29E-12 3.67E-12 2.77E-12 0.000 ng/dscm 1.06E-02 5.36E-03 4.06E-03 0.007 ng/dscm@7%O2 8.43E-03 4.25E-03 3.21E-03 0.005 

### Compound: 2,3,4,4',5-PeCB (PCB114) Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000508 0.00000004 0.0000000297 0.000 lb/mmBtuO2 3.03E-12 2.49E-12 1.90E-12 0.000 ng/dscm 4.42E-03 3.64E-03 2.78E-03 0.004 ng/dscm@7%O2 3.51E-03 2.89E-03 2.20E-03 0.003 

### Compound: 2,3',4,4',5-PeCB (PCB118) Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.00000207 0.00000134 0.000000993 0.000 lb/mmBtuO2 1.24E-10 8.33E-11 6.34E-11 0.000 ng/dscm 1.80E-01 1.22E-01 9.30E-02 0.132 ng/dscm@7%O2 1.43E-01 9.67E-02 7.35E-02 0.104 

### Compound: 2',3,4,4',5-PeCB (PCB123) Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000355 0.0000000247 0.0000000167 0.000 lb/mmBtuO2 2.12E-12 1.54E-12 1.07E-12 0.000 ng/dscm 3.09E-03 2.25E-03 1.56E-03 0.002 ng/dscm@7%O2 2.46E-03 1.78E-03 1.23E-03 0.002 

### Compound: 2,3,4,6,7,8-HxCDF Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000025 0.0000000027 0.0000000026 0.000 lb/mmBtuO2 1.49E-13 1.68E-13 1.66E-13 0.000 ng/dscm 2.18E-04 2.45E-04 2.43E-04 0.000 ng/dscm@7%O2 1.73E-04 1.94E-04 1.92E-04 0.000 

### Compound: 2,3,4,7,8-PeCDF Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000016 0.0000000014 0.0000000039 0.000 lb/mmBtuO2 9.56E-14 8.70E-14 2.49E-13 0.000



### Monday, February 14, 2011 Page 12 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 ng/dscm 1.39E-04 1.27E-04 3.65E-04 0.000 ng/dscm@7%O2 1.11E-04 1.01E-04 2.88E-04 0.000 

### Compound: 2,3,7,8-TCDD Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000032 0.0000000026 0.0000000023 0.000 lb/mmBtuO2 1.91E-13 1.62E-13 1.47E-13 0.000 ng/dscm 2.79E-04 2.36E-04 2.15E-04 0.000 ng/dscm@7%O2 2.22E-04 1.87E-04 1.70E-04 0.000 

### Compound: 2,3,7,8-TCDF Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000041 0.0000000032 0.0000000032 0.000 lb/mmBtuO2 2.45E-13 1.99E-13 2.04E-13 0.000 ng/dscm 3.57E-04 2.91E-04 3.00E-04 0.000 ng/dscm@7%O2 2.84E-04 2.31E-04 2.37E-04 0.000 

### Compound: 3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.00000000071 0.00000000069 0.00000000079 0.000 lb/mmBtuO2 4.24E-14 4.29E-14 5.04E-14 0.000 ng/dscm 6.18E-05 6.27E-05 7.40E-05 0.000 ng/dscm@7%O2 4.91E-05 4.97E-05 5.85E-05 0.000 

### Compound: 3,3',4,4',5-PeCB (PCB126) Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.000000011 0.0000000092 0.0000000032 0.000 lb/mmBtuO2 6.57E-13 5.72E-13 2.04E-13 0.000 ng/dscm 9.58E-04 8.36E-04 3.00E-04 0.001 ng/dscm@7%O2 7.62E-04 6.63E-04 2.37E-04 0.001 

### Compound: 3,3',4,4'-TCB (PCB77) Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.000000131 0.000000138 0.0000000603 0.000 lb/mmBtuO2 7.82E-12 8.58E-12 3.85E-12 0.000 ng/dscm 1.14E-02 1.25E-02 5.64E-03 0.010 ng/dscm@7%O2 9.07E-03 9.91E-03 4.46E-03 0.008 

### Compound: 3,4,4',5-TCB (PCB81) Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.00000000561 0.00000000665 0.00000000462 0.000 lb/mmBtuO2 3.35E-13 4.13E-13 2.95E-13 0.000 ng/dscm 4.89E-04 6.04E-04 4.32E-04 0.001 ng/dscm@7%O2 3.89E-04 4.79E-04 3.41E-04 0.000 

### Compound: OCDD Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3


### Monday, February 14, 2011 Page 13 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 Mass_mg 0.000000015 0.000000004 0.00000000989 0.000 lb/mmBtuO2 8.96E-13 2.49E-13 6.31E-13 0.000 ng/dscm 1.31E-03 3.64E-04 9.26E-04 0.001 ng/dscm@7%O2 1.04E-03 2.89E-04 7.32E-04 0.001 

### Compound: OCDF Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000049 0.0000000052 0.0000000057 0.000 lb/mmBtuO2 2.93E-13 3.23E-13 3.64E-13 0.000 ng/dscm 4.27E-04 4.73E-04 5.34E-04 0.000 ng/dscm@7%O2 3.40E-04 3.75E-04 4.22E-04 0.000 

### Compound: Total Dioxins Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.00000003609 0.0000000173 0.00000002589 0.000 lb/mmBtuO2 2.16E-12 1.08E-12 1.65E-12 0.000 ng/dscm 3.14E-03 1.57E-03 2.42E-03 0.002 ng/dscm@7%O2 2.50E-03 1.24E-03 1.91E-03 0.002 

### Compound: Total Furans Average RunNumber PTP2-23-1 PTP2-23-2 PTP2-23-3 Mass_mg 0.0000000279 0.00000002029 0.00000003318 0.000 lb/mmBtuO2 1.67E-12 1.26E-12 2.12E-12 0.000 ng/dscm 2.43E-03 1.84E-03 3.11E-03 0.002 ng/dscm@7%O2 1.93E-03 1.46E-03 2.46E-03 0.002



### Location: PTP2 - Gases - Method 10 Compound: Carbon Monoxide Average Run 2-CO-1 2-CO-2 2-CO-3 lb/mmBtuO2 4.33E-02 6.84E-02 9.47E-03 0.040 ppm 5.39E+01 8.62E+01 1.18E+01 50.633 ppm@7%O2 4.31E+01 6.81E+01 9.39E+00 40.197



### Location: PTP2 - Gases - Method 25A Compound: Total organic compounds (TOC) as Average Run 2-THC-1 2-THC-2 2-THC-3 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000 ppm 0.00E+00 0.00E+00 0.00E+00 0.000 ppm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000



### Location: PTP2 - Gases - Method 6C Compound: Sulfur Dioxide Average Run 2-SO2-1 2-SO2-2 2-SO2-3 lb/mmBtuO2 8.67E-01 9.40E-01 9.24E-01 0.910 ppm 4.72E+02 5.18E+02 5.05E+02 498.333 ppm@7%O2 3.77E+02 4.09E+02 4.02E+02 396.000



### Monday, February 14, 2011 Page 14 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Location: PTP2 - Gases - Method 7E 

### Compound: Nitrogen oxides (NOx) Average Run 2-NOx-1 2-NOx-2 2-NOx-3 lb/mmBtuO2 5.60E-01 5.73E-01 6.05E-01 0.579 ppm 4.25E+02 4.40E+02 4.60E+02 441.667 ppm@7%O2 3.40E+02 3.48E+02 3.66E+02 351.333



### Location: PTP2 - Metals - Method 29 

### Compound: Antimony Average RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3 Mass_mg 0.0734 0.425 0.395 0.298 Elb/hr 3.66E-02 2.10E-01 2.00E-01 0.149 lb/mmBtuO2 9.93E-06 5.36E-05 5.07E-05 0.000 mg/dscm 1.45E-02 7.87E-02 7.44E-02 0.056 mg/dscm@7%O2 1.15E-02 6.22E-02 5.88E-02 0.044 

### Compound: Arsenic Average RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3 Mass_mg 0.00352 0.0232 0.0223 0.016 Elb/hr 1.75E-03 1.15E-02 1.13E-02 0.008 lb/mmBtuO2 4.76E-07 2.93E-06 2.86E-06 0.000 mg/dscm 6.95E-04 4.30E-03 4.20E-03 0.003 mg/dscm@7%O2 5.53E-04 3.40E-03 3.32E-03 0.002 

### Compound: Beryllium Average RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3 Mass_mg 0.000202 0.00135 0.0011 0.001 Elb/hr 1.01E-04 6.68E-04 5.57E-04 0.000 lb/mmBtuO2 2.73E-08 1.70E-07 1.41E-07 0.000 mg/dscm 3.99E-05 2.50E-04 2.07E-04 0.000 mg/dscm@7%O2 3.17E-05 1.98E-04 1.64E-04 0.000 

### Compound: Cadmium Average RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3 Mass_mg 0.000158 0.000894 0.000812 0.001 Elb/hr 7.88E-05 4.43E-04 4.11E-04 0.000 lb/mmBtuO2 2.14E-08 1.13E-07 1.04E-07 0.000 mg/dscm 3.12E-05 1.66E-04 1.53E-04 0.000 mg/dscm@7%O2 2.48E-05 1.31E-04 1.21E-04 0.000 

### Compound: Chromium Average RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3 Mass_mg 0.0107 0.0444 0.044 0.033 Elb/hr 5.33E-03 2.20E-02 2.23E-02 0.017 lb/mmBtuO2 1.45E-06 5.60E-06 5.65E-06 0.000 mg/dscm 2.11E-03 8.22E-03 8.29E-03 0.006



### Monday, February 14, 2011 Page 15 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 mg/dscm@7%O2 1.68E-03 6.50E-03 6.55E-03 0.005 

### Compound: Cobalt Average RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3 Mass_mg 0.0398 0.224 0.228 0.164 Elb/hr 1.98E-02 1.11E-01 1.16E-01 0.082 lb/mmBtuO2 5.39E-06 2.83E-05 2.93E-05 0.000 mg/dscm 7.85E-03 4.15E-02 4.30E-02 0.031 mg/dscm@7%O2 6.24E-03 3.28E-02 3.40E-02 0.024 

### Compound: Filterable Particulate Average RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3 Mass_mg 35.5 239 228.6 167.700 Elb/hr 1.77E+01 1.18E+02 1.16E+02 83.900 lb/mmBtuO2 4.80E-03 3.02E-02 2.94E-02 0.021 mg/dscm 7.01E+00 4.43E+01 4.31E+01 31.470 mg/dscm@7%O2 5.57E+00 3.50E+01 3.41E+01 24.890 

### Compound: Lead Average RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3 Mass_mg 0.0177 0.0587 0.0561 0.044 Elb/hr 8.82E-03 2.91E-02 2.84E-02 0.022 lb/mmBtuO2 2.40E-06 7.41E-06 7.21E-06 0.000 mg/dscm 3.49E-03 1.09E-02 1.06E-02 0.008 mg/dscm@7%O2 2.78E-03 8.61E-03 8.38E-03 0.007 

### Compound: Manganese Average RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3 Mass_mg 0.0386 0.217 0.223 0.160 Elb/hr 1.92E-02 1.07E-01 1.13E-01 0.080 lb/mmBtuO2 5.22E-06 2.74E-05 2.86E-05 0.000 mg/dscm 7.62E-03 4.02E-02 4.20E-02 0.030 mg/dscm@7%O2 6.06E-03 3.18E-02 3.32E-02 0.024 

### Compound: Nickel Average RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3 Mass_mg 0.766 4.66 4.6 3.342 Elb/hr 3.82E-01 2.31E+00 2.33E+00 1.674 lb/mmBtuO2 1.04E-04 5.88E-04 5.91E-04 0.000 mg/dscm 1.51E-01 8.63E-01 8.67E-01 0.627 mg/dscm@7%O2 1.20E-01 6.82E-01 6.85E-01 0.496 

### Compound: Selenium Average RunNumber PTP2-29-1 PTP2-29-2 PTP2-29-3 Mass_mg 0.002 0.0194 0.0254 0.016 Elb/hr 9.97E-04 9.60E-03 1.29E-02 0.008 lb/mmBtuO2 2.71E-07 2.45E-06 3.26E-06 0.000 mg/dscm 3.95E-04 3.59E-03 4.79E-03 0.003



### Monday, February 14, 2011 Page 16 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

Process Run Data mg/dscm@7%O2 3.14E-04 2.84E-03 3.79E-03 0.002



### Location: PTP2 - PM - OTM - 27/28 Compound: Filterable Particulate Average RunNumber PTP2-27/28-2 PTP2-27/28-3 PTP2-27/28-1 Mass_mg 54.167 42.167 48.217 48.184 lb/mmBtuO2 2.59E-02 2.13E-02 2.55E-02 0.024 

### Compound: Filterable PM2.5 Average RunNumber PTP2-27/28-1 PTP2-27/28-2 PTP2-27/28-3 Mass_mg 35.833 42.508 32.858 37.066 lb/mmBtuO2 1.89E-02 2.04E-02 1.66E-02 0.019 

### Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber PTP2-27/28-1 PTP2-27/28-2 PTP2-27/28-3 Mass_mg 2.826 0.693 24.764 9.428 lb/mmBtuO2 1.49E-03 3.32E-04 1.25E-02 0.005 

### Compound: Organic Condensible Particulate Average RunNumber PTP2-27/28-1 PTP2-27/28-2 PTP2-27/28-3 Mass_mg 0.467 1.775 25.208 9.150 lb/mmBtuO2 2.47E-04 8.50E-04 1.27E-02 0.005 

### Compound: Total Particulate Average RunNumber PTP2-27/28-1 PTP2-27/28-2 PTP2-27/28-3 Mass_mg 51.509 56.635 92.139 66.761 lb/mmBtuO2 2.72E-02 2.71E-02 4.65E-02 0.034 

### Compound: Total PM2.5 Average RunNumber PTP2-27/28-1 PTP2-27/28-2 PTP2-27/28-3 Mass_mg 39.126 44.976 82.83 55.644 lb/mmBtuO2 2.07E-02 2.15E-02 4.18E-02 0.028



### Monday, February 14, 2011 Page 17 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 Process Run Data



### Run Name Value UOM Comments Target Value 1 Residual Oil (No. 6) Burned 28349 gal/hr Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 3/26/2010; Start - 12:45; End - 14:45 0



### 10 Residual Oil (No. 6) Burned 28346 gal/hr Method 027/028; Run PM-1; Date - 3/25/2010; Start - 17:19; End - 20:53 0

11 Residual Oil (No. 6) Burned 28375 gal/hr Method 027/028; Run PM-2; Date - 3/27/2010; Start - 09:12; End - 11:55 0

12 Residual Oil (No. 6) Burned 28448 gal/hr Method 027/028; Run PM-3; Date - 3/30/2010; Start - 21:44; End - 23:57 0

2 Residual Oil (No. 6) Burned 28349 gal/hr Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 3/26/2010; Start - 15:05; End - 17:05 0

3 Residual Oil (No. 6) Burned 28349 gal/hr Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 3/26/2010; Start - 17:25; End - 19:24 0



### 4 Residual Oil (No. 6) Burned 28346 gal/hr Method 23; Run D/F-1; Date - 3/26/2010; Start - 13:03; End - 22:58 0

5 Residual Oil (No. 6) Burned 28375 gal/hr Method 23; Run D/F-2; Date - 3/27/2010; Start - 09:10; End - 19:01 0

6 Residual Oil (No. 6) Burned 28448 gal/hr Method 23; Run D/F-3; Date - 3/30/2010; Start - 10:36; End - 19:05 0

7 Residual Oil (No. 6) Burned 28346 gal/hr Method 29; Run M-1; Date - 3/26/2010; Start - 15:03; End - 19:38 0



### Monday, February 14, 2011 Page 18 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 8 Residual Oil (No. 6) Burned 28448 gal/hr Method 29; Run M-2; Date - 3/30/2010; Start - 09:17; End - 13:38 0

9 Residual Oil (No. 6) Burned 28448 gal/hr Method 29; Run M-3; Date - 3/30/2010; Start - 14:17; End - 18:37 0

1 Average Heat Input 3537 MMBtu/hr Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 3/26/2010; Start - 12:45; End - 14:45 0



### 10 Average Heat Input 3537 MMBtu/hr Method 027/028; Run PM-1; Date - 3/25/2010; Start - 17:19; End - 20:53 0

11 Average Heat Input 3541 MMBtu/hr Method 027/028; Run PM-2; Date - 3/27/2010; Start - 09:12; End - 11:55 0

12 Average Heat Input 3550 MMBtu/hr Method 027/028; Run PM-3; Date - 3/30/2010; Start - 21:44; End - 23:57 0

2 Average Heat Input 3537 MMBtu/hr Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 3/26/2010; Start - 15:05; End - 17:05 0

3 Average Heat Input 3537 MMBtu/hr Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 3/26/2010; Start - 17:25; End - 19:24 0



### 4 Average Heat Input 3537 MMBtu/hr Method 23; Run D/F-1; Date - 3/26/2010; Start - 13:03; End - 22:58 0

5 Average Heat Input 3541 MMBtu/hr Method 23; Run D/F-2; Date - 3/27/2010; Start - 09:10; End - 19:01 0

6 Average Heat Input 3550 MMBtu/hr Method 23; Run D/F-3; Date - 3/30/2010; Start - 10:36; End - 19:05 0



### Monday, February 14, 2011 Page 19 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
7 Average Heat Input 3537 MMBtu/hr Method 29; Run M-1; Date - 3/26/2010; Start - 15:03; End - 19:38 0

8 Average Heat Input 3550 MMBtu/hr Method 29; Run M-2; Date - 3/30/2010; Start - 09:17; End - 13:38 0

9 Average Heat Input 3550 MMBtu/hr Method 29; Run M-3; Date - 3/30/2010; Start - 14:17; End - 18:37 0

1 Steam Output 2586 1000 lb Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 3/26/2010; Start - 12:45; End - 14:45 0



### 10 Steam Output 2574 1000 lb Method 027/028; Run PM-1; Date - 3/25/2010; Start - 17:19; End - 20:53 0

11 Steam Output 2571 1000 lb Method 027/028; Run PM-2; Date - 3/27/2010; Start - 09:12; End - 11:55 0

12 Steam Output 2582 1000 lb Method 027/028; Run PM-3; Date - 3/30/2010; Start - 21:44; End - 23:57 0

2 Steam Output 2586 1000 lb Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 3/26/2010; Start - 15:05; End - 17:05 0

3 Steam Output 2586 1000 lb Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 3/26/2010; Start - 17:25; End - 19:24 0

4 Steam Output 2581 1000 lb Method 23; Run D/F-1; Date - 3/26/2010; Start - 13:03; End - 22:58 0

5 Steam Output 2576 1000 lb Method 23; Run D/F-2; Date - 3/27/2010; Start - 09:10; End - 19:01 0



### Monday, February 14, 2011 Page 20 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
6 Steam Output 2576 1000 lb Method 23; Run D/F-3; Date - 3/30/2010; Start - 10:36; End - 19:05 0

7 Steam Output 2586 1000 lb Method 29; Run M-1; Date - 3/26/2010; Start - 15:03; End - 19:38 0

8 Steam Output 2575 1000 lb Method 29; Run M-2; Date - 3/30/2010; Start - 09:17; End - 13:38 0

9 Steam Output 2577 1000 lb Method 29; Run M-3; Date - 3/30/2010; Start - 14:17; End - 18:37 0

1 Unit Gross Electrical Output 392 MWg Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 3/26/2010; Start - 12:45; End - 14:45 0



### 10 Unit Gross Electrical Output 392 MWg Method 027/028; Run PM-1; Date - 3/25/2010; Start - 17:19; End - 20:53 0

11 Unit Gross Electrical Output 390 MWg Method 027/028; Run PM-2; Date - 3/27/2010; Start - 09:12; End - 11:55 0

12 Unit Gross Electrical Output 392 MWg Method 027/028; Run PM-3; Date - 3/30/2010; Start - 21:44; End - 23:57 0

2 Unit Gross Electrical Output 392 MWg Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 3/26/2010; Start - 15:05; End - 17:05 0

3 Unit Gross Electrical Output 392 MWg Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 3/26/2010; Start - 17:25; End - 19:24 0

4 Unit Gross Electrical Output 391 MWg Method 23; Run D/F-1; Date - 3/26/2010; Start - 13:03; End - 22:58 0



### Monday, February 14, 2011 Page 21 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 5 Unit Gross Electrical Output 391 MWg Method 23; Run D/F-2; Date - 3/27/2010; Start - 09:10; End - 19:01 0

6 Unit Gross Electrical Output 391 MWg Method 23; Run D/F-3; Date - 3/30/2010; Start - 10:36; End - 19:05 0

7 Unit Gross Electrical Output 392 MWg Method 29; Run M-1; Date - 3/26/2010; Start - 15:03; End - 19:38 0

8 Unit Gross Electrical Output 392 MWg Method 29; Run M-2; Date - 3/30/2010; Start - 09:17; End - 13:38 0

9 Unit Gross Electrical Output 392 MWg Method 29; Run M-3; Date - 3/30/2010; Start - 14:17; End - 18:37 0

1 Unit Net Electric Generation 372 MWn Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 3/26/2010; Start - 12:45; End - 14:45 0



### 10 Unit Net Electric Generation 372 MWn Method 027/028; Run PM-1; Date - 3/25/2010; Start - 17:19; End - 20:53 0

11 Unit Net Electric Generation 370 MWn Method 027/028; Run PM-2; Date - 3/27/2010; Start - 09:12; End - 11:55 0

12 Unit Net Electric Generation 372 MWn Method 027/028; Run PM-3; Date - 3/30/2010; Start - 21:44; End - 23:57 0

2 Unit Net Electric Generation 372 MWn Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 3/26/2010; Start - 15:05; End - 17:05 0

3 Unit Net Electric Generation 372 MWn Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 3/26/2010; Start - 17:25; End - 19:24 0



### Monday, February 14, 2011 Page 22 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010

APCD Run Data

Process Lab Run Data 4 Unit Net Electric Generation 371 MWn Method 23; Run D/F-1; Date - 3/26/2010; Start - 13:03; End - 22:58 0

5 Unit Net Electric Generation 371 MWn Method 23; Run D/F-2; Date - 3/27/2010; Start - 09:10; End - 19:01 0

6 Unit Net Electric Generation 372 MWn Method 23; Run D/F-3; Date - 3/30/2010; Start - 10:36; End - 19:05 0

7 Unit Net Electric Generation 372 MWn Method 29; Run M-1; Date - 3/26/2010; Start - 15:03; End - 19:38 0

8 Unit Net Electric Generation 372 MWn Method 29; Run M-2; Date - 3/30/2010; Start - 09:17; End - 13:38 0

9 Unit Net Electric Generation 372 MWn Method 29; Run M-3; Date - 3/30/2010; Start - 14:17; End - 18:37 0



### Run Name Value UOM Comments Target Value 1 LOW NOX BURNERS 395 NOx Emissions 0


### 2 LOW NOX BURNERS 403 NOx Emissions 0
3 LOW NOX BURNERS 423 NOx Emissions 0
1 CYCLONE SEPARATORS 4.7 Opacity 0


### 2 CYCLONE SEPARATORS 4.7 Opacity 0
3 CYCLONE SEPARATORS 4.9 Opacity 0

Run Name Value UOM Comments 

### 1 Fuel Higher Heating Value 18300 Btu/lb 1 Fuel Moisture 0.602 % 1 Fuel Mercury Content 0.005 mg/kg 1 Fuel Chlorine Content 110 mg/kg 

### 1 Fuel Fluorine Content 70 mg/kg 1 Fuel Antimony Content 1.8 mg/kg 1 Fuel Arsenic Content 0.078 mg/kg 

### 1 Fuel Beryllium Content 0.008 mg/kg
Monday, February 14, 2011 Page 23 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 1 Fuel Cadmium Content 0.011 mg/kg 

### 1 Fuel Chromium Content 0.15 mg/kg 1 Fuel Cobalt Content 0.79 mg/kg 1 Fuel Lead Content 0.42 mg/kg 1 Fuel Manganese Content 0.7 mg/kg 

### 1 Fuel Nickel Content 19.2 mg/kg 1 Fuel Selenium Content 0.03 mg/kg 1 Fuel Sulfur Content 8650 mg/kg 

### 1 Fuel Proximate Analysis (Carbon) 88.2 % 1 Fuel Proximate Analysis (Hydrogen) 10.25 % 1 Fuel Proximate Analysis (Nitrogen) 0.5 % 1 Fuel Proximate Analysis (Oxygen) 0.5 % 

### 1 Fuel Proximate Analysis (Sulfur) 0.97 % 2 Fuel Higher Heating Value 18300 Btu/lb 2 Fuel Moisture 1.12 % 

### 2 Fuel Mercury Content 0.007 mg/kg 2 Fuel Chlorine Content 120 mg/kg 2 Fuel Fluorine Content 78 mg/kg 2 Fuel Antimony Content 1.8 mg/kg 

### 2 Fuel Arsenic Content 0.094 mg/kg 2 Fuel Beryllium Content 0.008 mg/kg 2 Fuel Cadmium Content 0.011 mg/kg 

### 2 Fuel Chromium Content 0.16 mg/kg 2 Fuel Cobalt Content 0.82 mg/kg 2 Fuel Lead Content 0.42 mg/kg 2 Fuel Manganese Content 0.8 mg/kg 

### 2 Fuel Nickel Content 20.3 mg/kg 2 Fuel Selenium Content 0.03 mg/kg 2 Fuel Sulfur Content 8610 mg/kg 

### 2 Fuel Proximate Analysis (Carbon) 88.1 % 2 Fuel Proximate Analysis (Hydrogen) 10.32 % 2 Fuel Proximate Analysis (Nitrogen) 0.5 % 2 Fuel Proximate Analysis (Oxygen) 0.53 % 

### 2 Fuel Proximate Analysis (Sulfur) 0.977 % 3 Fuel Higher Heating Value 18300 Btu/lb 3 Fuel Moisture 0.678 % 

### 3 Fuel Mercury Content 0.010 mg/kg 3 Fuel Chlorine Content 110 mg/kg 3 Fuel Fluorine Content 74 mg/kg 3 Fuel Antimony Content 1.8 mg/kg 

### 3 Fuel Arsenic Content 0.11 mg/kg 3 Fuel Beryllium Content 0.008 mg/kg 3 Fuel Cadmium Content 0.003 mg/kg



### Monday, February 14, 2011 Page 24 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 3 Fuel Chromium Content 0.18 mg/kg 

### 3 Fuel Cobalt Content 0.82 mg/kg 3 Fuel Lead Content 0.43 mg/kg 3 Fuel Manganese Content 0.8 mg/kg 3 Fuel Nickel Content 19.7 mg/kg 

### 3 Fuel Selenium Content 0.03 mg/kg 3 Fuel Sulfur Content 9170 mg/kg 3 Fuel Proximate Analysis (Carbon) 87.49 % 

### 3 Fuel Proximate Analysis (Hydrogen) 10.11 % 3 Fuel Proximate Analysis (Nitrogen) 0.53 % 3 Fuel Proximate Analysis (Oxygen) 0.53 % 3 Fuel Proximate Analysis (Sulfur) 0.983 %



### Monday, February 14, 2011 Page 25 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010 Sampling / Stack Data Results Detail



### Location PTP2 - D/F - Method 23 Average Run Number PTP2-23-1 PTP2-23-2 PTP2-23-3 Test Date 3/26/2010 3/27/2010 3/30/2010 Run Start Time 1:03:00 PM 9:10:00 AM 10:36:00 AM Run Finish Time 10:58:00 PM 7:01:00 PM 7:05:00 PM Net Traversing Points 12 12 12 Net Run Time, minutes 480 480 480 Nozzle Diameter, inches 0.25 0.25 0.25 0.250 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.987 0.987 0.987 0.987 Barometric Pressure, inches of Mercury 29.68 29.71 29.68 29.690 Average Orifice Meter Differential, inches H2O 2.62 2.36 2.44 2.473 Dry Gas Meter Volume Sampled, cubic feet 422.260 401.780 390.110 404.717 Average Dry Gas Meter Temperature, °F 81.67 78.17 77.75 79.197 Dry Gas Meter Volume Sampled, dscf 405.610 388.589 377.292 390.497 Total Moisture Liquid collected, g 780.4 786.1 714 760.167 Volume of Water Vapor, standard cubic feet 36.73 37.00 33.61 35.780 Moisture Content of Stack Gas, % 8.30 8.69 8.18 8.390 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.917 0.9131 0.9182 0.916 Carbon Dioxide, % 14.51 14.67 14.7 14.627 Oxygen, % 3.42 3.37 3.31 3.367 Carbon Monoxide & Nitrogen, % 82.07 81.96 81.99 82.007 Fuel Factor 1.20 1.19 1.20 Dry Molecular Weight, lb/lb-Mole 30.46 30.48 30.48 30.473 Wet Molecular weight, lb/lb-Mole 29.43 29.40 29.46 29.430 Flue Gas Static Pressure, inches of H2O 1 1 1 1.000 Absolute Flue Gas Pressure, inches of Mercury 29.75 29.78 29.75 29.760 Average Stack Gas Temperature, °F 290.00 284.67 284.50 286.390 Average Velocity Head, inches of H2O 0.9319452576 11234 0.877443517

30358 0.910452885

68522 0.907
Average Stack Gas Velocity, feet/second 64.16 62.04 63.15 63.117 Stack Cross-Sectional Area, square feet 305.063 305.063 305.063 305.063 Dry Volumetric Flow Rate, dry scfm 753,828.4 731,752.3 748,421.1 744,667.267 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,174,370.5 1,135,566.5 1,155,883.7 1,155,273.5 67 Percent Isokinetic of Sampling Rate, % 100.3 99.0 94.0 97.767 Percent Excess Air, % 18.7 18.4 18.1 18.400 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Round Duct Diameter, inches 236.5 236.5 236.5 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 26 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
Location PTP2 - Gases - Method 10 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Monday, February 14, 2011 Page 27 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
Location PTP2 - Gases - Method 25A Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Monday, February 14, 2011 Page 28 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
Location PTP2 - Gases - Method 3A CO2 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Monday, February 14, 2011 Page 29 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
Location PTP2 - Gases - Method 3A O2 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Monday, February 14, 2011 Page 30 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
Location PTP2 - Gases - Method 6C Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Monday, February 14, 2011 Page 31 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
Location PTP2 - Gases - Method 7E Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Monday, February 14, 2011 Page 32 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
Location PTP2 - Metals - Method 29 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Monday, February 14, 2011 Page 33 of 34

### Turkey Point Energy Center, Unit #2, Information Collection Request

6/22/2010
Location PTP2 - PM - OTM - 27/28 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Monday, February 14, 2011 Page 34 of 34