### Name: Kevin Holbrooks

Title: Director, Environmental Compliance Company: St. Johns River Power Park Sign Date: Name: Carl Vineyard Title: MACT Utility Program Manager Company: Grace Consulting, Inc. Sign Date: 6/25/2010 Permitted Facility Representative / Date Testing Company Representative / Date 

## St. Johns River Power Park, Unit 1

Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Friday, February 04, 2011 Page 1 of 13

### St. Johns River Power Park, Unit 1

Facility Information:
St. Johns River Power Park 11201 New Berlin Road

Jacksonville FL 32226 Contact:Kevin Holbrooks Phone: 904-665-4540 Fax: 904-665-4530 Email: holbke@jea.com Testing Company: Grace Consulting, Inc. 510 Dickson Street

Wellington OH44090 Contact:Carl Vineyard Phone: 440-647-6672 Fax: 440-647-6673 Email: carlvineyard@aol.com

Air Permit Number: FL0037869 Permitted Source ID/Name: Unit 1 SJRPP Permitted Maximum Process Rate: 660 MW Max. Normal Operation Process Rate: 660 MW Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: SJRPP Unit 1 is a pulverized coal boiler rated at 660 MW with a SCR Electrostatic Precipitator and Scrubber

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information: AFS #: 1203100001 FRS #: 110000362134

SCC / Description10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous Coal - Pulverized Coal: Dry Bottom (Bituminous Coal)

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width Stack Unit 1 471.44 2350 600 4 0 24 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location Carbon Monoxide Method 10 3 120 0 Stack Unit 1 Total organic compounds

(TOC) as Propane Method 25A 3 120 0 Stack Unit 1

O2 Method 3A O2 3 120 0 Stack Unit 1 Co2 Method 3A CO2 3 120 0 Stack Unit 1 Nitrogen oxides (NOx) Method 7E 3 120 0 Stack Unit 1



### Friday, February 04, 2011 Page 2 of 13

### St. Johns River Power Park, Unit 1

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.
There were no modifications to the test methods.



### Friday, February 04, 2011 Page 3 of 13

### St. Johns River Power Park, Unit 1

Sampling / Stack Data Results Summary


### Location Stack Unit 1 - Method 10 Average Run Number 1 2 3 Test Date 4/6/2010 4/6/2010 4/6/2010 Run Start Time 8:45:00 AM 11:30:00 AM 2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM Carbon Dioxide, % 13.1 13.2 13.2 13.167 Oxygen, % 6.1 6.1 6.1 6.100 Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.00 0 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Moisture, % 13.6 14.33 14.17 14.033 Fuel Type Coal - Bituminous Coal -

Bituminous Coal -

Bituminous Fw 10640 10640 10640 10,640.000 Fc 1800 1800 1800 1,800.000



### Location Stack Unit 1 - Method 25A Average Run Number 1 2 3 Test Date 4/6/2010 4/6/2010 4/6/2010 Run Start Time 8:45:00 AM 11:30:00 AM 2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:00:00 PM Carbon Dioxide, % 13.1 13.2 13.2 13.167 Oxygen, % 6.1 6.1 6.1 6.100 Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.00 0 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Moisture, % 13.6 14.33 14.17 14.033 Fuel Type Coal - Bituminous Coal -

Bituminous Coal -

Bituminous Fw 10640 10640 10640 10,640.000 Fc 1800 1800 1800 1,800.000



### Friday, February 04, 2011 Page 4 of 13

### St. Johns River Power Park, Unit 1

Location Stack Unit 1 - Method 3A CO2 Average Run Number 1 2 3 Test Date 4/6/2010 4/6/2010 4/6/2010 Run Start Time 8:45:00 AM 11:30:00 AM 2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM Carbon Dioxide, % 13.1 13.2 13.2 13.167 Oxygen, % 6.1 6.1 6.1 6.100 Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.00 0 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Moisture, % 13.6 14.33 14.17 14.033 Fuel Type Coal - Bituminous Coal -

Bituminous Coal -

Bituminous Fw 10640 10640 10640 10,640.000 Fc 1800 1800 1800 1,800.000



### Location Stack Unit 1 - Method 3A O2 Average Run Number 1 2 3 Test Date 4/6/2010 4/6/2010 4/6/2010 Run Start Time 8:45:00 AM 11:30:00 AM 2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM Carbon Dioxide, % 13.1 13.2 13.2 13.167 Oxygen, % 6.1 6.1 6.1 6.100 Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.00 0 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Moisture, % 13.6 14.33 14.17 14.033 Fuel Type Coal - Bituminous Coal -

Bituminous Coal -

Bituminous Fw 10640 10640 10640 10,640.000 Fc 1800 1800 1800 1,800.000



### Friday, February 04, 2011 Page 5 of 13

### St. Johns River Power Park, Unit 1

Location Stack Unit 1 - Method 7E Average Run Number 1 2 3 Test Date 4/6/2010 4/6/2010 4/6/2010 Run Start Time 8:45:00 AM 11:30:00 AM 2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM Carbon Dioxide, % 13.1 13.2 13.2 13.167 Oxygen, % 6.1 6.1 6.1 6.100 Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.00 0 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Moisture, % 13.6 14.33 14.17 14.033 Fuel Type Coal - Bituminous Coal -

Bituminous Coal -

Bituminous Fw 10640 10640 10640 10,640.000 Fc 1800 1800 1800 1,800.000



### Friday, February 04, 2011 Page 6 of 13

### St. Johns River Power Park, Unit 1

Emissions Summary

Process Run Data 

### Location: Stack Unit 1 - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 lb/mmBtuO2 1.26E-01 1.39E-01 1.24E-01 0.130 ppm 1.25E+02 1.38E+02 1.23E+02 128.667 ppm@7%O2 1.17E+02 1.30E+02 1.16E+02 121.000



### Location: Stack Unit 1 - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 4.34E-04 3.14E-04 3.43E-04 0.000 ppm 2.75E-01 1.99E-01 2.17E-01 0.230 ppm@7%O2 2.58E-01 1.87E-01 2.04E-01 0.216



### Location: Stack Unit 1 - Method 7E Compound: Nitrogen oxides (NOx) Average Run 1 2 3 lb/mmBtuO2 1.01E-01 1.05E-01 1.04E-01 0.103 ppm 6.10E+01 6.34E+01 6.31E+01 62.500 ppm@7%O2 5.73E+01 5.95E+01 5.93E+01 58.700



### Friday, February 04, 2011 Page 7 of 13

### St. Johns River Power Park, Unit 1

Process Run Data

APCD Run Data

Process Lab Run Data 

### Run Name Value UOM Comments Target Value 1 Heat Input 6130 mmBtu 6000


### 2 Heat Input 6145 mmBtu 6000
3 Heat Input 6165 mmBtu 6000
1 Gross MW 675 MW 650


### 2 Gross MW 675 MW 650
3 Gross MW 675 MW 650
1 Steam Flow 4.63 Mlb/hr 4.5


### 2 Steam Flow 4.72 Mlb/hr 4.5
3 Steam Flow 4.75 Mlb/hr 4.5



### Run Name Value UOM Comments Target Value 1 SCR (SELECTIVE CATALYTIC REDUCTION) 661 lb/hr 600


### 2 SCR (SELECTIVE CATALYTIC REDUCTION) 686 lb/hr 600
3 SCR (SELECTIVE CATALYTIC REDUCTION) 699 lb/hr 600


### 1 Dual Alkali Scrubber 109 Kgpm 108
2 Dual Alkali Scrubber 108.7 Kgpm 108
3 Dual Alkali Scrubber 108.8 Kgpm 108


### 1 ELECTROSTATIC PRECIPITATOR
2 ELECTROSTATIC PRECIPITATOR
3 ELECTROSTATIC PRECIPITATOR


### 1 OVERFIRE AIR
2 OVERFIRE AIR
3 OVERFIRE AIR



### Friday, February 04, 2011 Page 8 of 13

### St. Johns River Power Park, Unit 1

Sampling / Stack Data Results Detail


### Location Stack Unit 1 - Method 10 Average Run Number 1 2 3 Test Date 4/6/2010 4/6/2010 4/6/2010 Run Start Time 8:45:00 AM11:30:00 AM 2:00:00 PM Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM Carbon Dioxide, % 13.1 13.2 13.2 13.167 Oxygen, % 6.1 6.1 6.1 6.100 Fuel Factor 1.13 1.12 1.12 Dry Volumetric Flow Rate, dry scfm 1776319 1783456 18060971,788,624.0 00 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Moisture, % 13.6 14.33 14.17 14.033 Analyzer Make Horiba Horiba Horiba Analyzer Model VIA-510 VIA-510 VIA-510 Analyzer Serial Number 570124044 570124044 570124044570,124,044 .000 Operating Range 497 497 497 497.000 Operating Units ppm ppm ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 1 1 1 1.000 Calibration Pre Zero Cylinder ID EB0020770 EB0020770 EB0020770 Calibration Pre Zero Cylinder Instrument Response 0.98 0.45 0.33 0.587 Calibration Pre Zero Cylinder Bias 0.19 0.08 0.06 0.110 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID EB0004477 EB0004477 EB0004477 Calibration Pre High Cylinder Instrument Response 231.19 232.28 234.49 232.653 Calibration Pre High Cylinder Bias -0.22 0 0.44 0.073 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID EB0020770 EB0020770 EB0020770 Calibration Post Zero Cylinder Instrument Response 0.45 0.33 0.99 0.590 Calibration Post Zero Cylinder Bias 0.08 0.06 0.19 0.110 Calibration Post Zero Cylinder Drift 0.11 0.02 0.13 0.087 Calibration Post High Cylinder ID EB0004477 EB0004477 EB0004477 Calibration Post High Cylinder Instrument Response 232.28 234.49 231.09 232.620 Calibration Post High Cylinder Bias 0 0.44 -0.24 0.067 Calibration Post High Cylinder Drift 0.22 0.44 0.68 0.447 Cavg 126.64 140.49 124.81 130.647 Cavg Units ppmvd ppmvd ppmvd Cgas 125.369 138.2991 123.0108 128.893 Cgas Units ppmvd ppmvd ppmvd Fuel Type Coal - Bituminous Coal -

Bituminous Coal -

Bituminous Fw 10640 10640 1064010,640.000 Fc 1800 1800 1800 1,800.000 Cgasw 0 0 0 0.000 Cgasw Units



### Friday, February 04, 2011 Page 9 of 13

### St. Johns River Power Park, Unit 1

Location Stack Unit 1 - Method 25A Average Run Number 1 2 3 Test Date 4/6/2010 4/6/2010 4/6/2010 Run Start Time 8:45:00 AM11:30:00 AM 2:00:00 PM Run Finish Time 11:00:00 AM 1:45:00 PM 4:00:00 PM Carbon Dioxide, % 13.1 13.2 13.2 13.167 Oxygen, % 6.1 6.1 6.1 6.100 Fuel Factor 1.13 1.12 1.12 Dry Volumetric Flow Rate, dry scfm 1776319 1783456 18060971,788,624.0 00 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Moisture, % 13.6 14.33 14.17 14.033 Analyzer Make Thermo Thermo Thermo Analyzer Model 51 51 51 51.000 Analyzer Serial Number 4723 4723 4723 4,723.000 Operating Range 9.03 9.03 9.03 9.030 Operating Units ppm pp ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 2 2 2 2.000 Calibration Pre Zero Cylinder ID EB0020770 EB0020770 EB0020770 Calibration Pre Zero Cylinder Instrument Response 0.05 0.06 0.03 0.047 Calibration Pre Zero Cylinder Bias -0.22 -0.11 -0.44 -0.257 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID CC13687 CC13687 CC13687 Calibration Pre High Cylinder Instrument Response 3.06 3.08 3.17 3.103 Calibration Pre High Cylinder Bias 0.22 0.44 1.44 0.700 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID EB0020770 EB0020770 EB0020770 Calibration Post Zero Cylinder Instrument Response 0.06 0.03 0.04 0.043 Calibration Post Zero Cylinder Bias -0.11 -0.44 -0.33 -0.293 Calibration Post Zero Cylinder Drift 0.11 0.33 0.11 0.183 Calibration Post High Cylinder ID CC13687 CC13687 CC13687 Calibration Post High Cylinder Instrument Response 3.08 3.17 3.21 3.153 Calibration Post High Cylinder Bias 0.44 1.44 1.88 1.253 Calibration Post High Cylinder Drift 0.22 1 0.44 0.553 Cavg 0.28 0.21 0.22 0.237 Cavg Units ppmvw ppmvw ppmvw Cgas 0.2747 0.1989 0.2173 0.230 Cgas Units ppmvd ppmvd ppmvd Fuel Type Coal - Bituminous Coal -

Bituminous Coal -

Bituminous Fw 10640 10640 10640 10,640.000 Fc 1800 1800 1800 1,800.000 Cgasw 0.2373134328 358210.170357142

857143 0.186465927

099842 0.198
Cgasw Units ppmvw ppmvw ppmvw



### Friday, February 04, 2011 Page 10 of 13

### St. Johns River Power Park, Unit 1

Location Stack Unit 1 - Method 3A CO2 Average Run Number 1 2 3 Test Date 4/6/2010 4/6/2010 4/6/2010 Run Start Time 8:45:00 AM11:30:00 AM 2:00:00 PM Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM Carbon Dioxide, % 13.1 13.2 13.2 13.167 Oxygen, % 6.1 6.1 6.1 6.100 Fuel Factor 1.13 1.12 1.12 Dry Volumetric Flow Rate, dry scfm 1776319 1783456 18060971,788,624.0 00 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Moisture, % 13.6 14.33 14.17 14.033 Analyzer Make Calif Analytical Calif

Analytical Calif

Analytical Analyzer Model 200 200 200 200.000 Analyzer Serial Number 1L05017 1L05017 1L05017 Operating Range 18.1 18.1 18.1 18.100 Operating Units % % % No. Readings/Avg. 120 120 120 120.000 Calibration Set 3 3 3 3.000 Calibration Pre Zero Cylinder ID EB0020770 EB0020770 EB0020770 Calibration Pre Zero Cylinder Instrument Response 0.02 0.08 0.07 0.057 Calibration Pre Zero Cylinder Bias -0.39 -0.06 -0.11 -0.187 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID EB0002789 EB0002789 EB0002789 Calibration Pre High Cylinder Instrument Response 9.03 9.05 9.02 9.033 Calibration Pre High Cylinder Bias -0.5 -0.39 -0.55 -0.480 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID EB0020770 EB0020770 EB0020770 Calibration Post Zero Cylinder Instrument Response 0.08 0.07 0.03 0.060 Calibration Post Zero Cylinder Bias -0.06 -0.11 -0.33 -0.167 Calibration Post Zero Cylinder Drift 0.33 0.05 0.22 0.200 Calibration Post High Cylinder ID EB0002789 EB0002789 EB0002789 Calibration Post High Cylinder Instrument Response 9.05 9.02 9.04 9.037 Calibration Post High Cylinder Bias -0.39 -0.55 -0.44 -0.460 Calibration Post High Cylinder Drift 0.11 0.16 0.11 0.127 Cavg 13.19 13.25 13.22 13.220 Cavg Units %vd %vd %vd Cgas 13.1108 13.1897 13.1553 13.152 Cgas Units %vd %vd %vd Fuel Type Coal - Bituminous Coal -

Bituminous Coal -

Bituminous Fw 10640 10640 1064010,640.000 Fc 1800 1800 1800 1,800.000 Cgasw 0 0 0 0.000 Cgasw Units



### Friday, February 04, 2011 Page 11 of 13

### St. Johns River Power Park, Unit 1

Location Stack Unit 1 - Method 3A O2 Average Run Number 1 2 3 Test Date 4/6/2010 4/6/2010 4/6/2010 Run Start Time 8:45:00 AM11:30:00 AM 2:00:00 PM Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM Carbon Dioxide, % 13.1 13.2 13.2 13.167 Oxygen, % 6.1 6.1 6.1 6.100 Fuel Factor 1.13 1.12 1.12 Dry Volumetric Flow Rate, dry scfm 1776319 1783456 18060971,788,624.0 00 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Moisture, % 13.6 14.33 14.17 14.033 Analyzer Make Calif Analytical Calif

Analytical Calif

Analytical Analyzer Model 200 200 200 200.000 Analyzer Serial Number 1L05017 1L05017 1L05017 Operating Range 22.4 22.4 22.4 22.400 Operating Units % % % No. Readings/Avg. 120 120 120 120.000 Calibration Set 4 4 4 4.000 Calibration Pre Zero Cylinder ID EB0020770 EB0020770 EB0020770 Calibration Pre Zero Cylinder Instrument Response 0.09 0.11 0.02 0.073 Calibration Pre Zero Cylinder Bias 0.18 0.27 -0.13 0.107 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID EB0002789A EB0002789 AEB0002789A
Calibration Pre High Cylinder Instrument Response 11.01 11.05 11.06 11.040 Calibration Pre High Cylinder Bias -0.13 0.04 0.09 0.000 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID EB0020770 EB0020770 EB0020770 Calibration Post Zero Cylinder Instrument Response 0.11 0.02 0.07 0.067 Calibration Post Zero Cylinder Bias 0.27 -0.13 0.09 0.077 Calibration Post Zero Cylinder Drift 0.09 0.4 0.22 0.237 Calibration Post High Cylinder ID EB0002789A EB0002789 AEB0002789A
Calibration Post High Cylinder Instrument Response 11.05 11.06 11.11 11.073 Calibration Post High Cylinder Bias 0.04 0.09 0.31 0.147 Calibration Post High Cylinder Drift 0.17 0.05 0.22 0.147 Cavg 6.19 6.17 6.2 6.187 Cavg Units %vd %vd %vd Cgas 6.129 6.1106 6.1327 6.124 Cgas Units %vd %vd %vd Fuel Type Coal - Bituminous Coal -

Bituminous Coal -

Bituminous Fw 10640 10640 1064010,640.000 Fc 1800 1800 1800 1,800.000 Cgasw 0 0 0 0.000 Cgasw Units



### Friday, February 04, 2011 Page 12 of 13

### St. Johns River Power Park, Unit 1

Location Stack Unit 1 - Method 7E Average Run Number 1 2 3 Test Date 4/6/2010 4/6/2010 4/6/2010 Run Start Time 8:45:00 AM11:30:00 AM 2:00:00 PM Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM Carbon Dioxide, % 13.1 13.2 13.2 13.167 Oxygen, % 6.1 6.1 6.1 6.100 Fuel Factor 1.13 1.12 1.12 Dry Volumetric Flow Rate, dry scfm 1776319 1783456 18060971,788,624.0 00 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Moisture, % 13.6 14.33 14.17 14.033 Analyzer Make Thermo Thermo Thermo Analyzer Model 42C 42C 42C Analyzer Serial Number 42chi_67507_ 35742chi_67507

_35742chi_67507_

357 Operating Range 125 125 125 125.000 Operating Units ppm ppm ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 5 5 5 5.000 Calibration Pre Zero Cylinder ID EB0020770 EB0020770 EB0020770 Calibration Pre Zero Cylinder Instrument Response 0.12 0.25 0.25 0.207 Calibration Pre Zero Cylinder Bias -0.02 0.08 0.08 0.047 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID EB0015104 EB0015104 EB0015104 Calibration Pre High Cylinder Instrument Response 84.65 84.33 84.89 84.623 Calibration Pre High Cylinder Bias -0.62 -0.88 -0.43 -0.643 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID EB0020770 EB0020770 EB0020770 Calibration Post Zero Cylinder Instrument Response 0.25 0.25 0.94 0.480 Calibration Post Zero Cylinder Bias 0.08 0.08 0.63 0.263 Calibration Post Zero Cylinder Drift 0.1 0 0.55 0.217 Calibration Post High Cylinder ID EB0015104 EB0015104 EB0015104 Calibration Post High Cylinder Instrument Response 84.33 84.89 85.58 84.933 Calibration Post High Cylinder Bias -0.88 -0.43 0.12 -0.397 Calibration Post High Cylinder Drift 0.26 0.45 0.55 0.420 Cavg 60.36 62.79 63.04 62.063 Cavg Units ppmvd ppmvd ppmvd Cgas 61.028 63.3851 63.0795 62.498 Cgas Units ppmvd ppmvd ppmvd Fuel Type Coal - Bituminous Coal -

Bituminous Coal -

Bituminous Fw 10640 10640 1064010,640.000 Fc 1800 1800 1800 1,800.000 Cgasw 0 0 0 0.000 Cgasw Units



### Friday, February 04, 2011 Page 13 of 13