### Instructionsfor Completing the Process Data Template

This template is to be used to record the 30 daily averages of specific process data required by the ICR. The ERT does not have the capability to store these daily averages. This spreadsheet included 4 separate surrogate worksheets,in case the boiler tested is tested for all surrogates at 4 different dates.This spreadsheet is intended to be used for one boiler of one facility.Data for multiple boilers should be handled by using separate copies of this spreadsheet. yelloware required (if applicable to your boilers' operation). You do not need to populate cells shaded in gray, as they ar automaticallypopulated from the Boiler Information worksheet. Please Do Not modify the structure of this spreadsheet by adding or subtracting rows, columns, cells. Pleasename each resulting spreadsheet with the following naming

convention:[FacilityID]_Unit_[BoilerID]_Processdata.xls(example: 8100_Unit_2_Processdata.xls).

Pleaserefer to the following steps when using these spreadsheets.

BoilerInformation Worksheet

Pleaseenter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Informationworksheet.

ProcessData Worksheets

Pleaseuse one process data worksheetfor each HAP surrogate even is simultaneous testing of different HAP surrogates was done.

### Instructionsfor Completing the Process Data Template

This template is to be used to record the 30 daily averages of specific process data required by the ICR. The ERT does not have the capability to store these daily averages. This spreadsheet included 4 separate surrogate worksheets,in case the This spreadsheet is intended to be used for one boiler of one facility.Data for multiple boilers should be handled by using separate copies of this spreadsheet. Fields shaded in yelloware required (if applicable to your boilers' operation). You do not need to populate cells shaded in gray, as they are Please Do Not modify the structure of this spreadsheet Pleasename each resulting spreadsheet with the following naming

convention:[FacilityID]_Unit_[BoilerID]_Processdata.xls(example: 8100_Unit_2_Processdata.xls).

Pleaseenter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Informationworksheet.

Pleaseuse one process data worksheetfor each HAP surrogate even is simultaneous testing of different HAP surrogatesEIA

Facility Code Facility Name Boiler ID

54081 Spruance Genco, LLC 2EIA

Facility Code Facility Name Boiler ID

54081 Spruance Genco, LLC 2

Daily A verage Process Data for a 30 Day Period Including the Testing Date Date Coal Firing Rate Coal Firing Rate (units) Synfuel Firing Rate Day 1 Day 2 Day 3 Day 4 Day 5 Day 6 Day 7 Day 8 Day 9 Day 10 Day 11 Day 12 Day 13 Day 14 Day 15 Day 16 Day 17 Day 18 Day 19 Day 20 Day 21 Day 22 Day 23 Day 24 Day 25 Day 26 Day 27 Day 28 Day 29 Day 30Daily A verage Process Data for a 30 Day Period Including the Testing Date Synfuel Firing Rate (units) Pet Coke Firing Rate Pet Coke Firing Rate (units) Coal Gas Firing RateCoal Gas Firing Rate (units) Fuel oil Firing Rate Fuel oil Firing Rate (units)Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr)Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe)Control Device Operating Parameters, A s Appicable Flue Gas Flow Rate (dscfm) Pressure Drop across FGD (in H2O)FGD Scrubber Liquor Flow Rate (gals/min) Sorbent Type Sorbent Injection Rate (lb/hr)Other Boiler or Control Device Operating Parameters (e.g., Boiler O2)

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%)EIA

Facility Code Facility Name Boiler ID

54081 Spruance Genco, LLC 2

Daily A verage Process Data for a 30 Day Period Including the Testing Date Date Coal Firing Rate Coal Firing Rate (units) Synfuel Firing Rate Day 1 Day 2 Day 3 Day 4 Day 5 Day 6 Day 7 Day 8 Day 9 Day 10 Day 11 Day 12 Day 13 Day 14 Day 15 Day 16 Day 17 Day 18 Day 19 Day 20 Day 21 Day 22 Day 23 Day 24 Day 25 Day 26 Day 27 Day 28 Day 29 Day 30Daily A verage Process Data for a 30 Day Period Including the Testing Date Synfuel Firing Rate (units) Pet Coke Firing Rate Pet Coke Firing Rate (units) Coal Gas Firing RateCoal Gas Firing Rate (units) Fuel oil Firing Rate Fuel oil Firing Rate (units)Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr)Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe)Control Device Operating Parameters, A s Appicable Flue Gas Flow Rate (dscfm) Pressure Drop across FGD (in H2O)FGD Scrubber Liquor Flow Rate (gals/min) Sorbent Type Sorbent Injection Rate (lb/hr)Other Boiler or Control Device Operating Parameters (e.g., Boiler O2)

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%)EIA

Facility Code Facility Name Boiler ID

54081 Spruance Genco, LLC 2

Daily A verage Process Data for a 30 Day Period Including the Testing Date Date Coal Firing Rate Coal Firing Rate (units) Synfuel Firing Rate Day 1 Day 2 Day 3 Day 4 Day 5 Day 6 Day 7 Day 8 Day 9 Day 10 Day 11 Day 12 Day 13 Day 14 Day 15 Day 16 Day 17 Day 18 Day 19 Day 20 Day 21 Day 22 Day 23 Day 24 Day 25 Day 26 Day 27 Day 28 Day 29 Day 30Daily A verage Process Data for a 30 Day Period Including the Testing Date Synfuel Firing Rate (units) Pet Coke Firing Rate Pet Coke Firing Rate (units) Coal Gas Firing RateCoal Gas Firing Rate (units) Fuel oil Firing Rate Fuel oil Firing Rate (units)Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr)Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe)Control Device Operating Parameters, A s Appicable Flue Gas Flow Rate (dscfm) Pressure Drop across FGD (in H2O)FGD Scrubber Liquor Flow Rate (gals/min) Sorbent Type Sorbent Injection Rate (lb/hr)Other Boiler or Control Device Operating Parameters (e.g., Boiler O2)

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%)EIA

Facility Code Facility Name Boiler ID

54081 Spruance Genco, LLC 2

Daily A verage Process Data for a 30 Day Period Including the Testing Date Date Coal Firing Rate Coal Firing Rate (units) Synfuel Firing Rate Day 1 04/01/10 17503 lbs/hr 0 Day 2 04/02/10 19879 lbs/hr 0 Day 3 04/03/10 23233 lbs/hr 0 Day 4 04/04/10 24517 lbs/hr 0 Day 5 04/05/10 54495 lbs/hr 0 Day 6 04/06/10 61541 lbs/hr 0 Day 7 04/07/10 62699 lbs/hr 0 Day 8 04/08/10 61702 lbs/hr 0 Day 9 04/09/10 58872 lbs/hr 0 Day 10 04/10/10 64965 lbs/hr 0 Day 11 04/11/10 62729 lbs/hr 0 Day 12 04/12/10 62623 lbs/hr 0 Day 13 04/13/10 62121 lbs/hr 0 Day 14 04/14/10 62024 lbs/hr 0 Day 15 04/15/10 64502 lbs/hr 0 Day 16 04/16/10 65644 lbs/hr 0 Day 17 04/17/10 54299 lbs/hr 0 Day 18 04/18/10 55452 lbs/hr 0 Day 19 04/19/10 62490 lbs/hr 0 Day 20 04/20/10 59070 lbs/hr 0 Day 21 04/21/10 64214 lbs/hr 0 Day 22 04/22/10 64688 lbs/hr 0 Day 23 04/23/10 67004 lbs/hr 0 Day 24 04/24/10 58377 lbs/hr 0 Day 25 04/25/10 54709 lbs/hr 0 Day 26 04/26/10 56997 lbs/hr 0 Day 27 04/27/10 60913 lbs/hr 0 Day 28 04/28/10 68992 lbs/hr 0 Day 29 04/29/10 67456 lbs/hr 0 Day 30 04/30/10 62664 lbs/hr 0Daily A verage Process Data for a 30 Day Period Including the Testing Date Synfuel Firing Rate (units) Pet Coke Firing Rate Pet Coke Firing Rate (units) Coal Gas Firing Rate N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0 N/A 0Coal Gas Firing Rate (units) Fuel oil Firing Rate Fuel oil Firing Rate (units)

N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/A N/A 0 N/AAverage Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr) 215 141330 244 159683 285 193379 301 197520 669 509708 755 509835 770 525672 757 509676 723 489951 797 550235 770 547064 769 527938 763 548792 761 545150 792 573479 806 582272 667 476265 681 487344 767 550076 725 522190 788 572723 794 575754 822 583523 717 492141 672 463637 700 467173 748 501387 847 554072 828 555214 769 513602Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe) -2.33 0.05 -1.50 0.00 -1.60 0.00 -1.79 0.00 47.98 50.89 48.02 50.60 50.77 53.41 48.21 50.82 46.29 48.79 54.00 56.68 53.91 56.64 50.40 53.01 55.23 57.99 55.92 58.70 58.25 61.08 59.15 61.99 45.16 47.71 47.11 49.75 55.16 57.90 51.46 54.11 58.81 61.56 58.41 61.20 58.60 61.38 46.62 49.18 43.29 45.72 43.14 45.55 47.81 50.35 54.52 57.26 55.68 58.48 49.31 51.94Control Device Operating Parameters, A s Appicable Flue Gas Flow Rate (dscfm) Pressure Drop across FGD (in H2O) 70051 0.00 75240 0.00 85089 0.00 98219 0.17 173310 1.59 163735 1.65 166844 1.60 167139 1.58 163958 1.53 175115 1.64 174744 1.66 169065 1.76 178683 1.82 178731 1.83 181189 1.87 181290 1.86 160114 1.55 164290 1.58 174526 1.71 167578 1.62 179583 1.80 179142 1.81 178724 1.84 156542 1.49 150367 1.35 153318 1.37 160711 1.49 173424 1.72 171768 1.74 165572 1.59FGD Scrubber Liquor Flow Rate (gals/min) Sorbent Type Sorbent Injection Rate (lb/hr) 0.10 Lime 199 0.13 Lime 115 0.62 Lime 141 0.10 Lime 153 1.46 Lime 359 17.71 Lime 371 23.30 Lime 409 4.75 Lime 439 10.50 Lime 515 4.89 Lime 377 27.62 Lime 322 31.40 Lime 361 33.12 Lime 305 24.63 Lime 318 12.80 Lime 328 0.07 Lime 332 0.09 Lime 281 0.28 Lime 412 2.40 Lime 524 2.87 Lime 586 6.54 Lime 596 10.04 Lime 473 16.67 Lime 455 17.74 Lime 342 0.10 Lime 394 10.73 Lime 606 4.14 Lime 593 19.13 Lime 574 1.49 Lime 471 4.96 Lime 460Other Boiler or Control Device Operating Parameters (e.g., Boiler O2)

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

-0.0076 151 -0.0087 143 -0.0107 142 -0.0124 165 -0.0246 181 -0.0228 190 -0.0229 186 -0.0234 183 -0.0233 181 -0.0249 180 -0.0251 179 -0.0241 183 -0.0264 180 -0.0267 179 -0.0271 179 -0.0269 181 -0.0229 182 -0.0238 178 -0.0261 174 -0.0243 174 -0.0266 174 -0.0267 176 -0.0269 178 -0.0230 179 -0.0215 179 -0.0216 177 -0.0228 176 -0.0258 175 -0.0259 175 -0.0242 177Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%)

Only measured during testing 5.7 Only measured during testing Only measured during testing 5.5 Only measured during testing Only measured during testing 5.5 Only measured during testing Only measured during testing 5.7 Only measured during testing Only measured during testing 11.1 Only measured during testing Only measured during testing 11.6 Only measured during testing Only measured during testing 12.5 Only measured during testing Only measured during testing 11.8 Only measured during testing Only measured during testing 11.2 Only measured during testing Only measured during testing 12.5 Only measured during testing Only measured during testing 12.7 Only measured during testing Only measured during testing 12.1 Only measured during testing Only measured during testing 12.6 Only measured during testing Only measured during testing 12.6 Only measured during testing Only measured during testing 12.9 Only measured during testing Only measured during testing 12.8 Only measured during testing Only measured during testing 11.8 Only measured during testing Only measured during testing 12.2 Only measured during testing Only measured during testing 13.0 Only measured during testing Only measured during testing 12.8 Only measured during testing Only measured during testing 12.9 Only measured during testing Only measured during testing 13.0 Only measured during testing Only measured during testing 13.1 Only measured during testing Only measured during testing 12.0 Only measured during testing Only measured during testing 11.4 Only measured during testing Only measured during testing 11.2 Only measured during testing Only measured during testing 11.8 Only measured during testing Only measured during testing 13.0 Only measured during testing Only measured during testing 13.2 Only measured during testing Only measured during testing 12.0 Only measured during testing