Name: Kevin Holbrooks

Title: Director, Environmental Compliance

Company: St. Johns River Power Park

Sign Date:

Name: Carl Vineyard

Title: MACT Utility Program Manager

Company: Grace Consulting, Inc.

Sign Date: 6/25/2010

Permitted Facility Representative / Date Testing Company Representative / Date

St. Johns River Power Park, Unit 1

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Friday, February 04, 2011 Page 1 of 13
St. Johns River Power Park, Unit 1

Facility Information:

St. Johns River Power Park

11201 New Berlin Road

Jacksonville FL 32226

Contact: Kevin Holbrooks

Phone: 904-665-4540

Fax: 904-665-4530

Email: holbke@jea.com

Testing Company:

Grace Consulting, Inc.

510 Dickson Street

Wellington OH 44090

Contact:Carl Vineyard

Phone: 440-647-6672

Fax: 440-647-6673

Email: carlvineyard@aol.com

Air Permit Number:

FL0037869

Permitted Source ID/Name:

SJRPP Unit 1

Permitted Maximum Process Rate:

660 MW

Max. Normal Operation Process Rate:

660 MW

Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

SJRPP Unit 1 is a pulverized coal boiler rated at 660 MW with a SCR Electrostatic Precipitator and Scrubber

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 1203100001 FRS #: 110000362134

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Unit 1 471.44 0 0 0 2350 600 4 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Unit 1 Carbon Monoxide Method 10 3 120 0

Total organic compounds 

(TOC) as Propane

Stack Unit 1 Method 25A 3 120 0

Stack Unit 1 O2 Method 3A O2 3 120 0

Stack Unit 1 Co2 Method 3A CO2 3 120 0

Stack Unit 1 Nitrogen oxides (NOx) Method 7E 3 120 0

Friday, February 04, 2011 Page 2 of 13
St. Johns River Power Park, Unit 1

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

There were no modifications to the test methods.

Friday, February 04, 2011 Page 3 of 13
St. Johns River Power Park, Unit 1

Sampling / Stack Data Results Summary

Location Stack Unit 1 - Method 10

Average

Run Number 1 2 3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 8:45:00 AM 11:30:00 

AM

2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM

Carbon Dioxide, % 13.1 13.2 13.2 13.167

Oxygen, % 6.1 6.1 6.1 6.100

Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.00

0

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.6 14.33 14.17 14.033

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location Stack Unit 1 - Method 25A

Average

Run Number 1 2 3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 8:45:00 AM 11:30:00 

AM

2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:00:00 PM

Carbon Dioxide, % 13.1 13.2 13.2 13.167

Oxygen, % 6.1 6.1 6.1 6.100

Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.00

0

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.6 14.33 14.17 14.033

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, February 04, 2011 Page 4 of 13
St. Johns River Power Park, Unit 1

Location Stack Unit 1 - Method 3A CO2

Average

Run Number 1 2 3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 8:45:00 AM 11:30:00 

AM

2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM

Carbon Dioxide, % 13.1 13.2 13.2 13.167

Oxygen, % 6.1 6.1 6.1 6.100

Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.00

0

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.6 14.33 14.17 14.033

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location Stack Unit 1 - Method 3A O2

Average

Run Number 1 2 3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 8:45:00 AM 11:30:00 

AM

2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM

Carbon Dioxide, % 13.1 13.2 13.2 13.167

Oxygen, % 6.1 6.1 6.1 6.100

Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.00

0

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.6 14.33 14.17 14.033

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, February 04, 2011 Page 5 of 13
St. Johns River Power Park, Unit 1

Location Stack Unit 1 - Method 7E

Average

Run Number 1 2 3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 8:45:00 AM 11:30:00 

AM

2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM

Carbon Dioxide, % 13.1 13.2 13.2 13.167

Oxygen, % 6.1 6.1 6.1 6.100

Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.00

0

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.6 14.33 14.17 14.033

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, February 04, 2011 Page 6 of 13
St. Johns River Power Park, Unit 1

Emissions Summary

Process Run Data

Location: Stack Unit 1 - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 1.26E-01 1.39E-01 1.24E-01 0.130

ppm 1.25E+02 1.38E+02 1.23E+02 128.667

ppm@7%O2 1.17E+02 1.30E+02 1.16E+02 121.000

Location: Stack Unit 1 - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 4.34E-04 3.14E-04 3.43E-04 0.000

ppm 2.75E-01 1.99E-01 2.17E-01 0.230

ppm@7%O2 2.58E-01 1.87E-01 2.04E-01 0.216

Location: Stack Unit 1 - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 1.01E-01 1.05E-01 1.04E-01 0.103

ppm 6.10E+01 6.34E+01 6.31E+01 62.500

ppm@7%O2 5.73E+01 5.95E+01 5.93E+01 58.700

Friday, February 04, 2011 Page 7 of 13
St. Johns River Power Park, Unit 1

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input 6130 mmBtu 6000

2 Heat Input 6145 mmBtu 6000

3 Heat Input 6165 mmBtu 6000

1 Gross MW 675 MW 650

2 Gross MW 675 MW 650

3 Gross MW 675 MW 650

1 Steam Flow 4.63 Mlb/hr 4.5

2 Steam Flow 4.72 Mlb/hr 4.5

3 Steam Flow 4.75 Mlb/hr 4.5

Run Name Value UOM Comments

Target

Value

1 SCR (SELECTIVE CATALYTIC REDUCTION) 661 lb/hr 600

2 SCR (SELECTIVE CATALYTIC REDUCTION) 686 lb/hr 600

3 SCR (SELECTIVE CATALYTIC REDUCTION) 699 lb/hr 600

1 Dual Alkali Scrubber 109 Kgpm 108

2 Dual Alkali Scrubber 108.7 Kgpm 108

3 Dual Alkali Scrubber 108.8 Kgpm 108

1 ELECTROSTATIC PRECIPITATOR

2 ELECTROSTATIC PRECIPITATOR

3 ELECTROSTATIC PRECIPITATOR

1 OVERFIRE AIR

2 OVERFIRE AIR

3 OVERFIRE AIR

Friday, February 04, 2011 Page 8 of 13
St. Johns River Power Park, Unit 1

Sampling / Stack Data Results Detail

Location Stack Unit 1 - Method 10

Average

Run Number 1 2 3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 8:45:00 AM 11:30:00 AM 2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM

Carbon Dioxide, % 13.1 13.2 13.2 13.167

Oxygen, % 6.1 6.1 6.1 6.100

Fuel Factor 1.13 1.12 1.12

Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.0

00

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.6 14.33 14.17 14.033

Analyzer Make Horiba Horiba Horiba

Analyzer Model VIA-510 VIA-510 VIA-510

Analyzer Serial Number 570124044 570124044 570124044 570,124,044

.000

Operating Range 497 497 497 497.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID EB0020770 EB0020770 EB0020770

Calibration Pre Zero Cylinder Instrument Response 0.98 0.45 0.33 0.587

Calibration Pre Zero Cylinder Bias 0.19 0.08 0.06 0.110

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID EB0004477 EB0004477 EB0004477

Calibration Pre High Cylinder Instrument Response 231.19 232.28 234.49 232.653

Calibration Pre High Cylinder Bias -0.22 0 0.44 0.073

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020770 EB0020770 EB0020770

Calibration Post Zero Cylinder Instrument Response 0.45 0.33 0.99 0.590

Calibration Post Zero Cylinder Bias 0.08 0.06 0.19 0.110

Calibration Post Zero Cylinder Drift 0.11 0.02 0.13 0.087

Calibration Post High Cylinder ID EB0004477 EB0004477 EB0004477

Calibration Post High Cylinder Instrument Response 232.28 234.49 231.09 232.620

Calibration Post High Cylinder Bias 0 0.44 -0.24 0.067

Calibration Post High Cylinder Drift 0.22 0.44 0.68 0.447

Cavg 126.64 140.49 124.81 130.647

Cavg Units ppmvd ppmvd ppmvd

Cgas 125.369 138.2991 123.0108 128.893

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 9 of 13
St. Johns River Power Park, Unit 1

Location Stack Unit 1 - Method 25A

Average

Run Number 1 2 3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 8:45:00 AM 11:30:00 AM 2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:00:00 PM

Carbon Dioxide, % 13.1 13.2 13.2 13.167

Oxygen, % 6.1 6.1 6.1 6.100

Fuel Factor 1.13 1.12 1.12

Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.0

00

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.6 14.33 14.17 14.033

Analyzer Make Thermo Thermo Thermo

Analyzer Model 51 51 51 51.000

Analyzer Serial Number 4723 4723 4723 4,723.000

Operating Range 9.03 9.03 9.03 9.030

Operating Units ppm pp ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 2 2 2 2.000

Calibration Pre Zero Cylinder ID EB0020770 EB0020770 EB0020770

Calibration Pre Zero Cylinder Instrument Response 0.05 0.06 0.03 0.047

Calibration Pre Zero Cylinder Bias -0.22 -0.11 -0.44 -0.257

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC13687 CC13687 CC13687

Calibration Pre High Cylinder Instrument Response 3.06 3.08 3.17 3.103

Calibration Pre High Cylinder Bias 0.22 0.44 1.44 0.700

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020770 EB0020770 EB0020770

Calibration Post Zero Cylinder Instrument Response 0.06 0.03 0.04 0.043

Calibration Post Zero Cylinder Bias -0.11 -0.44 -0.33 -0.293

Calibration Post Zero Cylinder Drift 0.11 0.33 0.11 0.183

Calibration Post High Cylinder ID CC13687 CC13687 CC13687

Calibration Post High Cylinder Instrument Response 3.08 3.17 3.21 3.153

Calibration Post High Cylinder Bias 0.44 1.44 1.88 1.253

Calibration Post High Cylinder Drift 0.22 1 0.44 0.553

Cavg 0.28 0.21 0.22 0.237

Cavg Units ppmvw ppmvw ppmvw

Cgas 0.2747 0.1989 0.2173 0.230

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Cgasw 0.2373134328

35821

0.170357142

857143

0.186465927

099842

0.198

Cgasw Units ppmvw ppmvw ppmvw

Friday, February 04, 2011 Page 10 of 13
St. Johns River Power Park, Unit 1

Location Stack Unit 1 - Method 3A CO2

Average

Run Number 1 2 3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 8:45:00 AM 11:30:00 AM 2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM

Carbon Dioxide, % 13.1 13.2 13.2 13.167

Oxygen, % 6.1 6.1 6.1 6.100

Fuel Factor 1.13 1.12 1.12

Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.0

00

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.6 14.33 14.17 14.033

Analyzer Make Calif 

Analytical

Calif 

Analytical

Calif 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 18.1 18.1 18.1 18.100

Operating Units % % %

No. Readings/Avg. 120 120 120 120.000

Calibration Set 3 3 3 3.000

Calibration Pre Zero Cylinder ID EB0020770 EB0020770 EB0020770

Calibration Pre Zero Cylinder Instrument Response 0.02 0.08 0.07 0.057

Calibration Pre Zero Cylinder Bias -0.39 -0.06 -0.11 -0.187

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID EB0002789 EB0002789 EB0002789

Calibration Pre High Cylinder Instrument Response 9.03 9.05 9.02 9.033

Calibration Pre High Cylinder Bias -0.5 -0.39 -0.55 -0.480

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020770 EB0020770 EB0020770

Calibration Post Zero Cylinder Instrument Response 0.08 0.07 0.03 0.060

Calibration Post Zero Cylinder Bias -0.06 -0.11 -0.33 -0.167

Calibration Post Zero Cylinder Drift 0.33 0.05 0.22 0.200

Calibration Post High Cylinder ID EB0002789 EB0002789 EB0002789

Calibration Post High Cylinder Instrument Response 9.05 9.02 9.04 9.037

Calibration Post High Cylinder Bias -0.39 -0.55 -0.44 -0.460

Calibration Post High Cylinder Drift 0.11 0.16 0.11 0.127

Cavg 13.19 13.25 13.22 13.220

Cavg Units %vd %vd %vd

Cgas 13.1108 13.1897 13.1553 13.152

Cgas Units %vd %vd %vd

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 11 of 13
St. Johns River Power Park, Unit 1

Location Stack Unit 1 - Method 3A O2

Average

Run Number 1 2 3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 8:45:00 AM 11:30:00 AM 2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM

Carbon Dioxide, % 13.1 13.2 13.2 13.167

Oxygen, % 6.1 6.1 6.1 6.100

Fuel Factor 1.13 1.12 1.12

Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.0

00

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.6 14.33 14.17 14.033

Analyzer Make Calif 

Analytical

Calif 

Analytical

Calif 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 22.4 22.4 22.4 22.400

Operating Units % % %

No. Readings/Avg. 120 120 120 120.000

Calibration Set 4 4 4 4.000

Calibration Pre Zero Cylinder ID EB0020770 EB0020770 EB0020770

Calibration Pre Zero Cylinder Instrument Response 0.09 0.11 0.02 0.073

Calibration Pre Zero Cylinder Bias 0.18 0.27 -0.13 0.107

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID EB0002789A EB0002789

A

EB0002789A

Calibration Pre High Cylinder Instrument Response 11.01 11.05 11.06 11.040

Calibration Pre High Cylinder Bias -0.13 0.04 0.09 0.000

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020770 EB0020770 EB0020770

Calibration Post Zero Cylinder Instrument Response 0.11 0.02 0.07 0.067

Calibration Post Zero Cylinder Bias 0.27 -0.13 0.09 0.077

Calibration Post Zero Cylinder Drift 0.09 0.4 0.22 0.237

Calibration Post High Cylinder ID EB0002789A EB0002789

A

EB0002789A

Calibration Post High Cylinder Instrument Response 11.05 11.06 11.11 11.073

Calibration Post High Cylinder Bias 0.04 0.09 0.31 0.147

Calibration Post High Cylinder Drift 0.17 0.05 0.22 0.147

Cavg 6.19 6.17 6.2 6.187

Cavg Units %vd %vd %vd

Cgas 6.129 6.1106 6.1327 6.124

Cgas Units %vd %vd %vd

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 12 of 13
St. Johns River Power Park, Unit 1

Location Stack Unit 1 - Method 7E

Average

Run Number 1 2 3

Test Date 4/6/2010 4/6/2010 4/6/2010

Run Start Time 8:45:00 AM 11:30:00 AM 2:00:00 PM

Run Finish Time 11:00:00 AM 1:45:00 PM 4:10:00 PM

Carbon Dioxide, % 13.1 13.2 13.2 13.167

Oxygen, % 6.1 6.1 6.1 6.100

Fuel Factor 1.13 1.12 1.12

Dry Volumetric Flow Rate, dry scfm 1776319 1783456 1806097 1,788,624.0

00

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.6 14.33 14.17 14.033

Analyzer Make Thermo Thermo Thermo

Analyzer Model 42C 42C 42C

Analyzer Serial Number 42chi_67507_

357

42chi_67507

_357

42chi_67507_

357

Operating Range 125 125 125 125.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 5 5 5 5.000

Calibration Pre Zero Cylinder ID EB0020770 EB0020770 EB0020770

Calibration Pre Zero Cylinder Instrument Response 0.12 0.25 0.25 0.207

Calibration Pre Zero Cylinder Bias -0.02 0.08 0.08 0.047

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID EB0015104 EB0015104 EB0015104

Calibration Pre High Cylinder Instrument Response 84.65 84.33 84.89 84.623

Calibration Pre High Cylinder Bias -0.62 -0.88 -0.43 -0.643

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020770 EB0020770 EB0020770

Calibration Post Zero Cylinder Instrument Response 0.25 0.25 0.94 0.480

Calibration Post Zero Cylinder Bias 0.08 0.08 0.63 0.263

Calibration Post Zero Cylinder Drift 0.1 0 0.55 0.217

Calibration Post High Cylinder ID EB0015104 EB0015104 EB0015104

Calibration Post High Cylinder Instrument Response 84.33 84.89 85.58 84.933

Calibration Post High Cylinder Bias -0.88 -0.43 0.12 -0.397

Calibration Post High Cylinder Drift 0.26 0.45 0.55 0.420

Cavg 60.36 62.79 63.04 62.063

Cavg Units ppmvd ppmvd ppmvd

Cgas 61.028 63.3851 63.0795 62.498

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 13 of 13