*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **1** of **93 EO12866_MATS_Reconsideration_2060**  **- AR62_Final_** **201303 19**  6560 - 50 - P **ENVIRONMENTAL PROTECTION AGENCY 40 CFR Parts 60 and 63**  **EPA -** **HQ -** **OAR -**  **2009 -**  **0234; EPA -** **HQ -** **OAR -**  **2011 -**  **0044 [**  **FRL -**  **9789 -**  **5 ]**  **RIN 2060**  **- AR62**  **Reconsideration of Certain New Source and Startup/Shutdown Issues: National Emission Standards for Hazardous Air Pollutants**  **from Coal -**  **and Oil -**  **fired Electric Utility Steam Generating Units and Standards of Performance for Fossil**  **- Fuel**  **- Fired Elect** **ric Utility, Industrial**  **- Commer** **c ial**  **- Institutional, and Small**  **Industrial -** **Commercial -**  **Institutional Steam Generating Units AGENCY:**  Environmental Protection Agency (EPA). **ACTION:** Final rule; notice of final action on reconsideration. **SUMMARY:** The EPA is taking final action on its reconsideration of certain issues in the final rules titled , “National Emission Standards for Hazardous Air Pollutants from Coal - and Oil - fired Electric Utility Steam Generating Units and Standards of Performance for Fossil - Fuel - Fired Electric Utility, Industrial Commercial - Institutional, and Small Industrial - Commercial Institutional Steam Generating Units. ” The National Emission Standards for Hazardous Air Pollutants (NESHAP) rule issued pursuant to Clean Air Act ( CAA ) section 112 is referred to as the Mercury and Air Toxics Standards (MATS) NESHAP , and the New*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **2** of **93** Source Performance Standards rule issued pursuant to CAA section 111 is referred to a s the Utility NSPS. The Administrator received petitions for reconsideration of certain aspects of the MATS NESHAP and the Utility NSPS. On November 30, 2012, the EPA granted reconsideration of, proposed, and requested comment on a limited set of issues . We also propos ed certain technical corrections to both the MATS NESHAP and the Utility NSPS . The EPA is now taking final action
on the revised new source numerical standards in the MATS NESHAP and the definitional and monitoring provisions in the Utility NSPS that were addressed in the proposed reconsideration rule . As part of this action, the EPA is also making certain technical corrections to both the MATS NESHAP and the Utility NSPS . The EPA is not taking final action on requirements applicable during periods of startup and shutdown in the MATS NESHAP or on startup and shutdown provisions related to the PM standard in the Utility NSPS . **DATES:** The effective date of the rule is **[ INSERT THE DATE OF**  **PUBLICATION IN THE FEDERAL REGISTER ]**  . Docket . The EPA established two dockets for this action: Docket ID EPA- HQ - OAR- 2011 - 0044 (NSPS action) and Docket ID EPA- HQ - OAR2009 - 0234 ( MATS NESHAP action) . All documents in the docket s are*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **3** of **93** listed in the http://www.regulations.gov index. Although listed in the index, some information is not publicly available (e.g., confidential business information ( CBI ) or other information whose disclosure is restricted by statute). Certain other material, such as copyrighted material, will be publicly available only in hard copy form. Publicly available docket materials are available either electronically in http://www.regulations.gov or in hard copy at the EPA Docket Center, Room 3334, 1301 Constitution Avenue, NW, Washington, DC. The Public Reading Room is open from 8:30 a.m. to 4:30 p.m., Monday through Friday, excluding legal holidays. The telephone number for the Public Reading Room is (202) 566 - 1744, and the telephone number for the Air Docket is (202) 566 - 1742. **FOR FURTHER INFORMATION CONTACT:** For the MATS NESHAP action: Mr. William Maxwell, Energy Strategies Group, Secto r Policies and Programs Division, (D243 - 01), Office of Air Quality Planning and Standards, U.S. Environmental Protection Agency, Research Triangle Park, North Carolina 27711; Telephone number: (919) 541 - 5430; Fax number (919) 541 - 5450; Email address: maxwell.bill@epa.gov . For the NSPS action: Mr. Christian Fellner, Energy Strategies Group, Sector Policies and Programs Division, (D243 - 01), Office of Air Quality Planning and*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **4** of **93** Standards, U.S. Environmental Protection Agency, Research Triangle Park, North Carolina 27711; Telephone number: (919) 541 - 4003; Fax number (919) 541 - 5450; Email address: fellner.christian@epa.gov . **SUPPLEMENTARY INFORMATION:** Outline . The information presented in this preamble is organized as follows: I. General Information A. Does this action apply to me? B. How do I obtain a copy of this document? C. Judicial Review II. Background III. Summary of Today ’ s Action IV. Summary of Final Action and Changes Since Proposal

– MATS NESHAP New Source Issues V. Summary of Final Action and Changes Since Proposal

– Utility NSPS VI. Technical Corrections and Clarifications VII. Impacts of this Final Rule A. Summary of Emissions Impacts, Costs and Benefit s B . What are the air impacts? C . What are the energy impacts? D . What are the compliance costs? E . What are the economic and employment impacts? F . What are the benefits of the final standards? VIII. Statutory and Executive Order Reviews A. Executive Order 12866: Regulatory Planning and Review and Executive Order 13563: Improving Regulation and Regulatory Review B. Paperwork Reduction Act C. Regulatory Flexibility Act D. Unfunded Mandates Reform Act E. Executive Order 13132: Federalism F. Executive Order 13175: Consultation and Coordination With Indian Tribal Governments G. Executive Order 13045: Protection of Children from*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **5** of **93** Environmental Health Risks and Safety Risks H. Executive Order 13211: Actions that Significantly Affect Energy Supply, Distribution , or Use I. National Technology Transfer and Advancement Act J. Executive Order 12898: Federal Actions to Address Environmental Justice in Minority Populations and Low- income Populations K. Congressional Review Act **I. General Information** A. Does this acti on apply to me ? Categories and entities potentially affected by today ’ s action include: Category NAICS code 1 Examples of potentially

regulated entities Industry 221112 Fossil fuel - fired electric utility steam generating units. Federal government 221122 2 Fossil fuel - fired electric utility steam generating units owned by the Federal government. State/local/Tribal government 221122 2
921150 Fossil fuel - fired electric

utility steam generating units owned by municipalities. Fossil fuel - fired electric utility steam generating units in Indian country. 1 North American Industry Classification System. 2 Federal, State, or local government - owned and operated establishments are classified according to the activity in which they are engaged. This table is not intended to be exhaustive but rather to provide a guide for readers regarding entities likely to be affected by this action. To determine whether your facility, company, business, organization, etc. would be regulated by this*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **6** of **93** action, you should examine the app licability criteria in 40 CFR 60.40, 60.40Da, or 60.40c or in 40 CFR 63.9982. If you have any questions regarding the applicability of this action to a particular entity, consult either the air permitting authority for the entity or your EPA regional repre sentative as listed in 40 CFR 60.4 or 40 CFR 63.13 (General Provisions). B. How do I obtain a copy of this document ? In addition to being available in the docket, electronic copies of these final rules will be available on the Worldwide Web (WWW) through the Technology Transfer Network (TTN). Following signature, a copy of the action will be posted on the TTN ’ s policy and guidance page for newly proposed or promulgated rules at the following address: http://www. epa.gov/ttn/oarpg/ . The TTN provides information and technology exchange in various areas of air pollution control. C. Judicial Review Under the CAA section 307(b)(1), judicial review of this final rule is available only by filing a petition for review in the U.S. Court of Appeals for the District of Columbia Circuit by **[ INSERT DATE 60 DAYS FROM DATE OF PUBLICATION IN THE FEDERAL**  **REGISTER ]**  . Under CAA section 307(d)(7)(B), only an objection to this final rule that was raised with reasonable specificity*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **7** of **93** during the period for public comment can be raised during judicial review. Note, under CAA section 307(b)(2), the requirements established by this final rule may not be challenged separately in any civil or criminal proceedings brought by the EPA to enforce these requirements. **II. Background** The final MATS NESHAP and the Utility NSPS rules were published in the Federal Register at 77 FR 9304 on February 16, 2012. Following promulgation of the final rules, the Administrator received petitions for reconsideration of numerous provisions of both the MATS NESHAP and the Utility NSPS pursuant to CAA section 307(d)(7)(B). Copies of the MATS NESHAP petitions are provided in rulemaking docket EPA- HQ - OAR- 2009 - 0234. Copies of the Utility NSPS petitions are provided in rulemaking docket EPA- HQ - OAR- 2011 - 0044. On November 30, 2012, the proposal granting reconsideration of certain issues in the MATS NESHAP and Utility NSPS was published in the Federal Register at 77 FR 71323 . **III. Summary of**  **Today ’**  **s Action** This final action amends certain provisions of the final rule issued by the EPA on February 16, 2012 . Through an August 2, 2012, notice (77 FR 45967), the EPA delaye d the effective*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **8** of **93** date of the February 2012 rule for new sources only . That stay was limited to 90 days and has since expired. The February 2012 final rule is and remains in effect for all sources . The November 30, 2012, proposed reconsideration rule proposed: (1) certain revised new source numerical standards in the MATS NESHAP , (2) requirements applicable during periods of startup and shutdown in the MATS NESHAP , (3) startup and shutdown provisions related to the particulate matter ( PM ) standard in the Utility NSPS, and (4) definitional and monitoring provisions in the Utility NSPS. We also propos ed certain technical corrections to both the MATS NESHAP and the Utility NSPS . We are taking final action today on the revised numerical new source MATS NESHAP limits, the definitional and monitoring issues in the Utility NSPS, and all of the technical corrections not related to startup/shutdown issues . This summary of the final rule reflects the changes to 40 CFR Part 63, subpart UUUUU, and 40 CFR Part 60, subpart Da ( 77 FR 9304; February 16, 2012 ) made in this regard . As noted above, i n the proposed reconsideration rule, the EPA took comment on the requirements in the MATS NESHAP applicable during startup and shutdown, including the definitions of startup and shutdown. The EPA also took comment*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **9** of **93** on the startup and shutdown provisions relating to the PM standard in the Utility NSPS. The EPA received considerable comments regarding these startup and shutdown provisions, including data and information relevant to the proposed work practice standard that applies in such periods . The EPA is not taking final action on the startup and shutdown issues at this time as it needs additional time to consider and evaluate the comments and data provided. 1 The Agency is currently reviewing all of the comments received on the startup and shutdown issues and intends to act promptly to address these issues. We note that no existing sources will have to comply with the existing source MATS standards before April 16, 2015. Further, no new sources are currently under construction and it takes years to complete construction . 77 FR 71330, fn . 7. As such, there will be sufficient time for the Agency to review the comments submitted concerning the proposed startup and shutdown provisions and take appropriate action well in advance of any new source being subject to the standards. As described below, on the basis of information provided since the reconsideration proposal, today ’ s action revises

1 The EPA is also still reviewing the other issues raised in the petitions for reconsideration and is not taking any action at this time with respect to those issues.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **10** of **93** certain new source numerical limits in the MATS NESHAP . Specifically, the EPA is finalizing revised hydrogen chloride (HCl), filterable PM (fPM), 2 sulfur dioxide (SO 2 ), lead (Pb), and selenium emission limits for all new coal - fired EGUs ; the mercury (Hg) emission limit for the “ unit designe d for coal > 8,300 Btu/lb subcategory ; ” fPM and SO 2 emission limits for new solid oil - derived fuel - fired EGUs; fPM emission limits for new continental liquid oil - fired EGUs; and most of the emission limits for new integrated gasification combined cycle ( IGCC ) units. The f PM, HCl, and Hg limits that we are finalizing in this action are provided in table 1; the alternate limits that we are finalizing are provided in table 2. 3 TABLE 1 . REVISED EMISSION LIMITATIONS FOR NEW EGUS Subcategory Filterable

particu late matter , lb/MWh Hydrogen chloride , lb/MWh Mercury ,

lb/GWh New - Unit not designed for low rank virgin coal 9.0E - 2 1.0E - 2 a 3.0E - 3 New - Unit designed for low rank 9.0E - 2 1.0E - 2 a NR

2 As the final MATS rule established a filterable PM (fPM) limit, every mention of a PM limit means filterable PM. 3 The final rule included certain alternative limits (see 77 FR 9367

– 9369).*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **11** of **93** virgin coal New
– IGCC 7.0E - 2 b 9.0E - 2 c 2.0E - 3 3.0E - 3 New
– Solid oil - derived 3 .0E - 2 NR NR New
– Liquid oil - continental 3 .0E - 1 NR NR Note: lb/MWh = pounds pollutant per megawatt
-hour electric output (gross) lb/GWh = pounds pollutant per gigawatt
-hour electric output (gross) NR = limit not opened for reconsideration (77 FR 9304; February 16, 2012) a Beyond- the - floor value b Duct burners on syngas; based on permit levels in comments received c Duct burners on natural gas; based on permit levels in comments received TABLE 2 . REVISED ALTERNATE EMISSION LIMITATIONS FOR NEW EGUS Subcategory / Pollutant Coal - fired EGUs IGCC a Solid oil derived SO 2 1.0 lb/MWh 4.0E - 1 lb/MWhb 1.0 lb/MWh Total non mercury metals NR 4.0E - 1 lb/GWh NR Antimony, Sb NR 2.0E - 2 lb/GWh NR Arsenic, As NR 2.0E - 2 lb/GWh NR Beryllium, Be NR 1.0E - 3 lb/GWh NR Cadmium, Cd NR 2.0E - 3 lb/GWh NR Chromium, Cr NR 4.0E - 2 lb/GWh NR Cobalt, Co NR 4.0E - 3 lb/GWh NR Lead, Pb 2 .0E - 2 lb/GWh 9.0E - 3 lb/GWh NR Mercury, Hg NA NA NR Manganese, Mn NR 2.0E - 2 lb/GWh NR Nickel, Ni NR 7.0E - 2 lb/GWh NR Selenium, Se 5.0E - 2 lb/GWh 3.0E - 1 lb/GWh NR NA = not applicable NR = limit not opened for reconsideration (77 FR 9304; February 16, 2012)*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **12** of **93** a Based on best -performing similar source b Based on DOE information In addition, in the MATS NESHAP the EPA is removing quarterly stack testing as an option to demonstrate compliance with the new source f PM emission limits; revising the way in which an owner or operator of a new EGU who chooses to use PM continuous parameter monitoring systems ( CPMS ) establishes an operating limit; requiring inspections and retesting within 45 days of an exceedance of the operating limit for those new EGU owners or operators who choose to use PM CPMS as a compliance option; and retain ing the presumption of violation of the emissions limit if more than 4 emissions tests are required in a 12 -month period . These final changes incorporate information about the variability of the best performing EGU s and more accurately reflect the capabilities of emission control equipment for new EGU s . The final changes should also address commenter s ’ concerns that vendors of EGU emission controls had been unwilling to provide guarantees regarding the ability to mee t all of the standards for new EGU s as originally finalized in February 2012 . We expect that source owners and operators will install and operate the same or similar control technologies to meet the*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **13** of **93** revised standards in this reconsideration action as they would have chosen to comply with the standards in the February 2012 final rule. Consistent with CAA section 112(a)(4), we are maintaining the new source trigger date for the MATS NESHAP rule as May 3, 2011. See 77 FR 71330, fn. 7. New sources must comply with the revised MATS emission standards described in section IV below by [INSERT DATE OF PUBLICATION OF RULE IN FEDERAL REGISTER], or startup, whichever is later. I n the February 2012 final Utility NSPS rule , the EPA adopted a definition of natural gas that excludes coal - derived synthetic natural gas consistent wi th the definition in MATS . In the Utility NSPS reconsideration proposal, we re -proposed and requested comment on that definition. Based on review of the comments received in response to the reconsideration proposal , the EPA has concluded that the definition of natural gas in the final Utility NSPS is appropriate and, therefore, is not making any changes to that definition . We are also finalizing as proposed one conforming amendment and two amendments related to EGUs burning desulfurized coal - derived synthetic natural gas . First, we amended the definition of coal to make it clear that coal - derived synthetic natural gas is considered to be coal . In addition, in recognition of the fact that emissions from the*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **14** of **93** burning of desulfurized coal - derived syntheti c natural gas are very similar to those from the burning of natural gas, we amended the opacity and SO 2 monitoring provision s so that facilities burning desulfurized coal - derived synthetic natural gas will have opacity and SO 2 monitoring requirements simil ar to those of facilities burning natural gas. Further, we are finalizing certain revisions to the definition of IGCC in the Utility NSPS. We are also finalizing as proposed the revised procedures for calculating PM emission rates intended to make the Util ity NSPS procedures consistent with those in the MATS NESHAP. We did not receive any adverse comments regarding this proposed change . Finally, we are finalizing as proposed the technical corrections to the PM standards for facilities that commenced constru ction before March 1, 2005, and for facilities that commence modification after May 3, 2011. The impacts of today’s revisions on the costs and the benefits of the final rule are minor . As noted above, we expect that source owners and operators will install and operate the same or similar control technologies to meet the revised standards in this action as they would have chosen to comply with the standards in the February 2012 final ru le. **IV. Summary of**  **Final Action and Changes Since Proposal**  **– MATS** *** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **15** of **93 NESHAP**  **New Source Issues** After consideration of the public comments received, the EPA has made certain changes in this final action from the reconsideration proposal. We address the most significant comments in this preamble. However for a complete summary of the comments received on the issues we are finalizing today and our responses thereto, please refer to the memorandum “National Emission Standards For Hazardous Air Pollutants From Co al - And Oil - Fired Electric Utility Steam Generating Units

– Reconsideration ; Summary Of Public Comments And Responses ” (March 2013) in rulemaking docket EPA- HQ - OAR- 2009 - 0234 . In this action , we are finalizing certain new source emission limits for the MATS NESHAP , as discussed below. 1. Changes to Certain New Source MATS NESHAP Limits Commenters noted that in two instances, Pb emissions from coal - fired EGUs and the fPM emissions from continental liquid oil - fired EGUs, the EPA had proposed new source emissi on limits that were less stringent than those in the final MATS NESHAP for the respective existing sources. This approach was inconsistent with that taken in the final MATS NESHAP . 4 Although CAA section

4 See “ National Emission Standards for Hazardous Air Pollutants (NESHAP) Maximum Achievable Control Technology (MACT) Floor*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **16** of **93** 112(d)(3) allows existing source MACT floor limits to be less stringent than new source limits, the EPA interprets this provision as precluding new source limits from being less stringent than existing source limits. See CAA section 112(d)(3). Thus, for Pb emissions from coal - fired EGUs and fPM emissions from continental liquid oil - fired EGUs, the EPA is finalizing new source limits that are equivalent to the final existing- source limits. Next, commenters noted that when evaluating SO 2 emissions data from coal - fired EGUs, the EPA had not selected the lowest emitting source upon which to base the emission limit and that its rationale for excluding certain data was unlawful and arbitrary. Although the EPA disagrees with commenter s on several of the excluded data sets ( i.e., some of the data sets suggested by commenter s comprised only a single 3 - run average for each EGU with no individual run data , making assessment of variability impossible) , it agrees that it inadvertently omitted the data from Stanton Unit 10 in the proposal analyses. Stanton Unit 10 does have a lower “ lowest ” 3 - run data average than does the EGU selected for the new source analysis (Sandow Unit 5A) in the Analysis for Coal - and Oil -fired Electric Utility Steam Generating Units for Final Rule ,” Docket ID EPA- HQ - OAR- 2009 - 0234 - 20132 , p. 13 .*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **17** of **93** proposed reconsideration rule . In this final action , the EPA used the Stanton data to calculate the MACT floor using the same statistical analyses used in the proposed rule (i.e., 99 percent upper predictive limit (UPL)), and the resulting MACT floor emission limit is 1.3 pounds per megawatt -hour ( lb/MWh ) . Because this limit is less stringent than the new source performance standard (NSPS) finalized in the Utility NSPS (77 FR 9451; February 16, 2012) , the EPA is finalizing a beyond- the - floor (BTF) MACT standard of 1.0 lb/MWh , which is the same level require d by the CAA section 111 NSPS for these same sources. 5 See 40 CFR 60.43Da(l)(1)(i) . Cost is a required consideration in establishing CAA section 111 rules and in going BTF in establishing CAA section 112 rules . We evaluated cost in assessing whether to go BTF for this standard and concluded that it was appropriate to go BTF to a level of 1.0 lb/MWh . Moreover, the NSPS limit (also 1.0 lb/MWh) is in place and coal - fired EGU s are required to comply with that

5 The CAA section 111 standard is based on the performance of EGUs with the best performing SO 2 controls, a reasonable incremental cost effectiveness of less than $1,000 per ton of SO 2 controlled, and controls that result in minimal secondary environmental and energy impacts.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **18** of **93** limit . As such , there is no additional cost to these sources . 6 Furthermore, we have not identif ied any non - air quality health or environmental impacts or energy requirements associated with the final standard set at this level. In addition, at reconsideration proposal, we evaluated going BTF more stringent than the NSPS level and found it not to be cost effective. 7 For these reasons, we are finalizing 1.0 lb/MWh as the new source MATS NESHAP limit, which is the same limit required for SO 2 emissions for new coal - fired EGUs under the Utility NSPS. In the proposed reconsideration rule, we indicated that detection level issues may arise from using a sorbent trap when short sampling periods (e.g., 30 minutes) are used . As such, the EPA solicited comment on its establishment of a Representative Detection Level (RDL) associated with Hg sorbent traps. The EPA also solicited comment on whether the UPL calculated floor should be compared against the 3XRDL value for Hg to account for the shorter samp ling periods (the 3XRDL approach). The EPA

6 The final Utility NSPS limit was not challenged and coal - fired EGUs cons tructed after May 3, 2011, must meet that limit . 7 See Docket ID EPA- HQ - OAR- 2009 - 0234 - 20221 and National Emission Standards for Hazardous Air Pollutants (NESHAP) Beyond the Maximum Achievable Control Technology (MACT) Floor (‘Beyond- the Floor’) Analysis for Revised Emission Standards for New Source Coal -and Oil -fired Electric Utility Steam Generating Units also in the rulemaking docket.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **19** of **93** received several comments, ranging from strong support for the Hg RDL and the proposed emission limit because, at that level, the commenters asserted that vendors would be able to provide commercial guarantees, to concerns about the specific inputs to the 3XRDL calculation and the application of the 3xRDL approach. See section 2.2.1 of the response to comments document ( RTC ) for a more complete discussion and response to these comments. In the proposed reconsideration rule, the EPA recognized that 30 minutes of sample collection is the shortest reasonable amount of time available for collecting and changing sorbent tubes to provide the quick, reliable feedback that will a llow sources to react to changing Hg emissions levels and assure compliance with the final Hg limit. Some commenter s pointed out that the EPA ’ s memorandum entitled “ Determination of Representative Detection Level (RDL) and 3 X RDL Values for Mercury Measured Using Sorbent Trap Technologies, ” 8 contains a 30 -minute sample collection time in the 3XRDL calculation, but the text of the memorandum references a 20 -minute sample

8 The EPA developed the memorandum to determine appropriate RDL and 3XRDL values for sorbent trap monitoring systems, as well as calculate an emissions limit, in order to determine the shortest, reasonable sample collection period for those systems . See EPA Docket ID EPA- HQ - OAR- 2009 - 0234 - 20222.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **20** of **93** collection time. The EPA has revised the text of the memorandum to reflect its original intent, which was to focus on a sample collection period of 30 minutes (not 20 minutes) . The revised memorandum focuses on the 30 -minute sample collection period. Given that it takes 5 minutes for sorbent trap insertion and removal, it would take a total of 40 minutes to secure the requisite sample collection (30 minutes for sample collection, 5 minutes to remove the sorbent trap, and 5 minutes to re - insert the trap). We are finalizing the Hg limit using the 3XRDL approach assuming a 30 -minute sampling time. 2 . Filterable PM Testing, Monitoring , and Compliance Certification for New EGUs in the MATS NESHAP Rule S everal monitoring options for the f PM standard for new sources were provided in the MATS NESHAP final rule, including quarterly stack testing, PM CEMS, and PM CPMS with annual testing . The EPA sought comment on whether to retain the quarterly stack testing compliance option for new EGUs, given that continuous, direct measurement of fPM or a correlat ed parameter is available , is preferable for determining compliance on a continuous basis, and is likely to be used by most new EGUs to monitor compliance with the proposed new source standards . As*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **21** of **93** mentioned above , this final action does not retain the quarterly f PM performance testing option for new EGUs . New EGUs can be designed to incorporate PM CEMS or PM CPMS from the outset , without being impeded by retrofit location installation constraints that could impact existing EGUs . Thi s final action now requires new sources to use either PM CEMS or PM CPMS as options for determining compliance with the new source f PM limits . The EPA requested comment on a number of issues associated with PM CPMS. The EPA identified three approaches to establish an operating limit based on emissions testing for those EGU owners or operators who choose to use PM CPMS as the means of demonstrating compliance with the fPM emission limit. The first approach, which was proposed and contained in the final MATS NESHAP rule, would require an EGU owner or operator to use the highest parameter value obtained during any run of an individual emissions test as the operating limit. The second approach would require an EGU owner or operato r to use the average parameter value obtained from all runs of an individual emissions test as the operating limit, provided that the result of the individual emissions test met the emissions limit. The third approach, which the EPA is finalizing in this f inal action, would require*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **22** of **93** an EGU owner or operator to use the higher of the following: (1) a parameter scaled from all values obtained during an individual emissions test to 75 percent of the emissions limit or (2) the average parameter value obtained from all runs of an individual emissions test as the operating limit, provided that the result of the individual emissions test met the emissions limit. As established and reaffirmed in the recent Sewage Sludge Incineration, Major Source Industrial Boiler, and Portland Cement rules , 9 increased operational flexibility and reduced emissions testing are available for those sources which emit at or below 75 percent of a standard

– whether an emissions or operating limit. Reduced emissions testing is available in this final rule for those owners or operators whose EGU emissions do not exceed this 75 percent threshold. This 75 percent threshold allows for compliance flexibility and is simultaneously protective of the emission s tandards . The EPA believes well

9 See Standards of Performance for New Stationary Sources and Emission Guidelines for Existing Sources: Commercial and Industrial Solid Waste Incineration Units , 76 FR 15736 (March 21, 2011) ; Subpart DDDDD

— National Emission Standards for Hazardous Air Pollutants for Major Sources: Industrial, Commercial, and Institutional Boilers and Process Heaters , 40 CFR 63.7515(b) ; and National Emission Standards for Hazardous Air Pollutants for the Portland Cement Manufacturing Industry and Standards of Perfor mance for Portland Cement Plants , 78 FR 10014 (February 12, 2013) .*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **23** of **93** performing EGUs, i.e., those whose emissions do not exceed 75 percent of the emissions limit, should not face additional scrutiny or testing consequences provided their emissions remain equivalent to or below the 75 percent threshold. In this final action, the EPA uses the 75 percent threshold so as not to impose unintended and costly retest requirements for the lowest emitting sources and to provide for more cost effective, continuous, PM parametric monitoring across the EGU sector. This approach was selected from the options considered as it provides the greatest amount of EGU owner or operator flexibility while demonstrating continuous compliance for EGU s. With this parametric monitoring approach in place , the EPA expect s EGUs t o evaluate control options that provide excellent f PM emissions control and provide them greater operational flexibility. Moreover, after each exceedance of the operating limit, the EPA proposed to require emissions testing to verify or re - adjust the operating limit, consistent with the approach contained in the recently-promulgated Portland cement MACT standard (see 78 FR 10014). One commenter objected to potential frequent emissions testing to reassess the operating limit and then being subject to a violation of the emissions limit . The EPA does not believe that too - frequent testing will be required. As discussed*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **24** of **93** in section 4.3.5 of the RTC, the EPA believes well - designed emissions testing will provide an operating limit corresponding with EGU operation , and such testing should yield an operating limit that would not be expected to be exceeded during the course of EGU operation. Therefore, an operating limit developed from well - designed emissions testing should have little, if any, need for frequent reassessment via emissions testing more frequently than the mandated annual reassessment because the source will be able to meet the limit on an ongoing basis . Finally, the EPA proposed that PM CPMS exceedances leading to more than 4 required emissions tests in a 12 -month period (rolling monthly) would be presumed (subject to the possibility of rebuttal by the EGU owner or operator) to be a violation of the emissions limit, consistent with the approach contained in the newly-promulgated Portland cement MACT standard (see 78 FR 10014). The EPA received a number of comments on this proposed provision, including comments supporting and opposing the establishment of such a presumption. The EPA disagrees with those comments opposing the pre sumptive violation, and believes the presumptive violation provision in the final rule is a reasonable and appropriate approach to ensure compliance with the standard. First, the EPA*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **25** of **93** may permissibly establish such an approach by rule, assuming there is a reasonable factual basis to do so. See Hazardous Waste Treatment Council v. EPA , 886 F. 2d 355, 367

– 68 (DC Cir. 1989) ( explaining that such presumptions can legitimately establish the elements of the EPA ’ s prima facie case in an enforcement action ) . Second, there is a reasonable basis here for the presumption that four exceedances (i.e. , increases over the parametric operating limit) in a calendar year are a violation of the emission standard. The parametric monitoring limit is established as a 30 - day average of the averaged test value in the performance test, or the 75 th percentile value if that is higher. In either instance, the 30 - day averaging feature provides significant leeway to the EGU owner or operator not to deviate from the parametric operating level because use of the hourly values collected during 30 boiler operating days will significantly dampen variability in the single measurement (average of three test runs) that produced the parametric value. See 77 FR 42377/2 and sources there cited. See also 78 FR 10015, 10019; February, 12, 2013 (Portland Cement MACT) and the RTC for today’s action. The EPA also received comments addressing the re - testing requirements following an exceedance. Some commenters expressed*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **26** of **93** concern about the burden of requir i ng sources to conduct performance tests in order to demonstrate compliance and to reassess the parameter level . In contrast, other commenters supported a requirement to require re - testing but claimed that the time period between observing a parameter excee dance and retesting is too long . The EPA believes that the re - testing requirements are reasonable and appropriate to identify non compliance without imposing undue burden. For even a single exceedance to occur, the 30 - day average would have to be higher than the operating limit established for the PM CPMS during normal EGU operation. If that occurs, then the EGU owner or operator is required to conduct an inspection to determine any abnormalities and an emissions test to re - establish or generate a new operating limit. Given that EGUs and their emissions control devices are designed to operate at known, specific conditions, deviations from these conditions are not expected and are indicative of problems with load, controls, or some combination of both. Where these sorts of problems result in an exceedance of the source’s operating limit, it is reasonable to require re - testing in order to identify and then correct problems. More than four such exceedances of the 30 - day average would mean that the EGU owner or operator was unable to*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **27** of **93** determine or correct the problem, since inspection and re calculation of the operating limit is required after each exceedance. This indicates an ongoing problem with maintaining process control and/or control device operation, which would be the basis for a presumptive violation of the emissions standard. Moreover, the EPA disagrees that the period between exceedance of the operating limit and retesting is too long and could result in possible excessive emissions. Specifically, some commenters claimed that the final rule should not limit the number of exceedances of the PM CPMS limit that require followup performance tests in any 12 -month period . These commenters alleged that to do so does not ensure continuous c ompliance because the time period between an exceedance and testing could be too long , and a source could be exceeding the emission limit during that time period . The EPA believes that the re - testing requirements reflect a reasonable balance between ensuring compliance and limiting unnecessary testing burden on regulated
sources. An EGU owner or operator is required to visually inspect the air pollution control device within 48 hours of the exceedance, and corrective action must be taken as soon as possible to return the PM C PMS measurement to within the established value. A performance test is also required within 45*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **28** of **93** days of the exceedance to determine compliance and verify or re establish the PM CPMS limit. Thus, the EPA finds it unlikely that there will be long periods of non compliance with the underlying f PM standard given the inspection and performance testing requirements. The EPA also received comments stating that an EGU owner or operator should not be labeled a “ violator ” of the fPM standard as a result of a fourth succe ssful compliance test in a 12 -month period . First, the EPA notes that the presumption of a violation is just that

– a presumption

– and can be rebutted in any particular case. Moreover, in determining whether the presumption has been successfully rebutted, a Court may consider relevant information such as data or other information showing that the EGU’s operating process remained in control during the period of operating paramet er exceedance, that the ongoing operation and maintenance conducted on the EGU ensured its emissions control devices remained in proper operating condition during the period of operating parameter exceedance, and that results of emissions tests conducted while replicating the conditions observed during the period of operating parameter exceedance remained below the emission limit. For the reasons explained above , this final action includes*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **29** of **93** the presumption of violation of the emissions limit if more than 4 emissions tests are required in a 12 -month period. **V. Summary of**  **Final Action and Changes Since Proposal**  **– Utility**  **NSPS** The EPA has made a number of changes from the reconsideration proposal in this final action after consideration of the public comments received. Most are changes to clarify applicability and implementation issues raised by the commenter s. The public comments received on the matters proposed for reconsideration and the responses to them can be viewed in the memorandum “ Summary of EGU NSPS Public Comments and Responses on Amendments Proposed November 30, 2012 (77 FR 71323) ” in rulemaking docket EPA- HQ - OAR- 2011 - 0044 . In the proposed reconsideration rule, the EPA proposed a new definition for IGCC whi ch would be consistent with the MATS NESHAP definition . However, as an alternative we also specifically requested comment on whether to retain a definition similar , but not identical, to the IGCC definition in the February 2012 final Utility NSPS. We have concluded that the alternative approach is most appropriate and are adopting a slightly revised definition that is consistent with the Agency’s statements on IGCC contained in the RTC in support of the final*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **3 0**  of **93** rule published on February 16, 2012 (77 FR 9304). Commenters generally supported amending the final Utility NSPS definition of IGCC , and this final action amends that definition consistent with the statements made in the RTC for the Utility NSPS. The Utility NSPS definition deals with the intent of an IGCC facility and is, thus, broader than the MATS NESHAP definition . The facility would still be subject to the same criteria pollutant emission standards even when burning natural gas for extended periods of time. The MATS NESHAP applicability is determined based on the EGUs utilization of coal and oil and the rule may not apply depending on the extent of natural gas usage. The EPA proposed that the NSPS PM monitoring procedures be consistent with the MATS NESHAP requirements and included the use of quarterly stack testing, PM CPMS, or PM CEMS. In addition, the EPA sought comment on whether to include the quarterly stack testing compliance option for new EGUs, given that continuous, direct measurement of PM or a correlated parameter is available. EGUs complying with an output -based emissions standard can be designed to incorporate PM CEMS or PM CPMS from the outset, without being impeded by retrofit location installation constraints that would impact existing EGUs. This final action requires EGUs complying with an output -based*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **31** of **93** standard to use either PM CEMS or PM CPMS as options for determining compliance with the PM limits. Therefore, the EPA is finalizing the same monitoring procedures for PM for the Utility NSPS as for new sources subject to the MATS NESHAP , and is not finalizing the quarterly stack testing option . The EPA proposed that facilities using PM CPMS would be able to use either a continuous opacity monitoring system or a periodic alternate monitoring approach to monitor opacity. This final action does not require facilities using a PM CPMS to conduct opacity monitoring. The EPA has concluded that the use of a PM CPMS at the level of the emissions standard required in subpart Da is sufficient to demonstrate compliance with the opacity standard and that additional monitoring is an unnecessary burden. **VI. Technical Corrections and Clarifications** On April 19, 2012 (77 FR 23399), the EPA issued a technical corrections notice addressing certain corrections to the February 16, 2012 (77 FR 9304) , MATS NESHAP and Utility NSPS . In the November 30, 2012 , reconsideration proposal , we propos ed several additional technical corrections. Specific to the NSPS, we proposed correcting the PM standard for facilities that commenced construction before March 1, 2005, to remove the extra*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **32** of **93** significant digit that was inadvertently added and to correct the PM standa rd for facilities that commence modification after May 3, 2011, to be consistent with the original intent as expressed in the RTC of the final rule published on February 16, 2012 ( 77 FR 9304 ). We did not receive any negative comments on these issues and are finalizing them as proposed. Specific details are included in Table 3. Specific to the MATS NESHAP, the EPA requested comment on whether the proposed technical corrections in Table 4 of the preamble provide the intended accuracy, clarity, and consistency . As mentioned in section 6.3 of the RTC, commenter s supported the proposed changes on equations 2a and 3a and th is final action contains those changes. As mentioned in section 6.3 of the RTC, commenter s did not support the change from a 30 to 60 day notification period for performance testing, and that change was not made to the rule; however, a change to the General Provisions applicability table was made to provide a consistent 30 - day notification per iod. Commenters suggested changes to certain definitions to make them more consistent with the Acid Rain rule provisions, but as described in section 6.4 of the RTC, these rule changes were not made. These amendments
are now being finalized to correct inac curacies and other*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **33** of **93** inadvertent errors in the final rule and to make the rule language consistent with provisions addressed through this reconsideration. The final technical changes are described in tables 3 and 4 of this preamble. TABLE 3 . MISCELLANEOUS TE CHNICAL CORRECTIONS TO 40 CFR PART 60, SUBPART Da **Section of subpart Da Description of correction**  40 CFR 60.42Da(a) Correct the erroneous “ 0.030 ” to the correct “ 0. 0 3 ” 40 CFR 60.42Da(e)(1)(ii) Correct the erroneous conversion “ 13 ng/J (0.015 lb/MMBtu) ” to the correct “ 6.4 ng/J (0.015 lb/MMBtu) ” by amending the regulatory text to specify that the requirements in 40 CFR 60.42Da(c) or (d), which includes two additional alternative limits, are available compliance alternatives for modified facilities TABLE 4 . MISCELLANEOUS TECHNICAL CORRECTIONS TO 40 CFR PART 63, SUBPART UUUUU **Section of subpart UUUUU Description of correction**  40 CFR 63.9982(a) Clarify the language to use the word “ or ” instead of “ and. ” 40 CFR 63.9982(b) and (c) Correct the discrepancy between 63.9982(b) and (c) and 63.9985(a) 40 CFR 63.10005(d)(2)(ii) Correct the typographical error by replacing the incorrect*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **34** of **93** “ corresponding ” with the correct “ corresponds. ” 40 CFR 63.10005(i)(4)(ii) and (i)(5) and add 63.10005(i)(6) Revise to clarify the determination and measurement of fuel moisture content. 40 CFR 63.10006(c) Correct the omission of solid oil - derived fuel - and coal - fired EGUs and IGCC EGUs and the omission of section 10000(c). 40 CFR 63.10007(c) Correct the omission of section 63.10023 from the list of sections to be followed in establishing an operating limit. 40 CFR 63.10009(b)(2) Correct omission of the term “boiler operating ” and c larify the term “ Rt i ” in Equation 2a. 40 CFR 63.10009(b)(3) Correct omission of the term “ sys tem” and c larify the term “ Rt i ” in Equation 3a. 40 CFR 63.10010(j)(1)(i) Correct the typographical error to use the correct word “ your ” instead of “ you. ” 40 CFR 63.10030(b), (c), and (d) Clarify the affected- source language. Change the period by which a Notification of Intent to conduct a performance test must be submitted to conform to the General Provisions. 40 CFR Section 63.10042 Correct the typographical error in the intended definition of “ unit designed for coal ≥ 8,300 Btu/lb subcategory” by repl acing the erroneous “ >“ with the correct “ ≥. ” Table 5 to Subpart UUUUU of Part 63 Correct the typographical error in footnote 4 by replacing the erroneous “ >“ with the correct “ < . ”*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **35** of **93** Table 7 to Subpart UUUUU of Part 63 Clarify the applicability of the alternate 90 - day average for Hg in item 1. Revise item 3 in the table to clarify use of CMS for liquid oil - fired EGUs. Table 9 to Subpart UUUUU of Part 63 Revise to clarify the period for notification of conducting a performance test from 60 to 30 days. Section 4.1 to Appendix A to Subpart UUUUU of Part 63 Correct the typographical error by replacing the incorrect citation to “ §63.10005(g) ” with the correct “ §63.9984(f). ” Section 5.2.2.2 to Appendix A to Subpart UUUUU of Part 63 Correct the typographica l error by replacing the incorrect citation to “ Table A- 4 ” with the correct “ Table A- 2 ” Section 3.1.2.1.3 to Appendix B to Subpart UUUUU of Part 63 Correct the typographical error by replacing the erroneous “ >“ with the correct “ < . ” Section 5.3.4 to Appendix B to Subpart UUUUU of Part 63 Correct the section number from the incorrect “ 5.3.4 ” to the correct “ 5.3.3. ” **VII. Impacts of this Final**  **Rule** A. Summary of Emissions Impacts, Costs and Benefits Our analysis shows that new EGUs would choose to install and operate the same or similar air pollution control technologies in order to meet the revised emission limits as would have been necessary to meet the previously finalized standards . We project that this final action will result in no*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **36** of **93** significant change in costs, emission reductions, or benefits. 10 Even if there were changes in costs for these EGU s, such changes would likely be small relative to both the overall costs of the individual projects and the overall costs and benefits of the final rule. Further, we believe that EGUs would put on the same controls for this final action that they would have for the original final MATS rule , so there should not be any incremental costs related to this revision. B . What are the air impacts ? We believe that electric power companies will install the
same or similar control technologies to comply with the final standards in this action as they would have installed to comply with the previously finalized MATS standards. Accordingly, we believe that this final action will not result in significant changes in emissions of any of the regulated pollutants. C . What are the energy impacts ? This final action is not anticipated to have an effect on

10 See Regulatory Impact Analysis for the Final Mercury and Air Toxics Standards [EPA- 452/R
- 11 - 011] (docket entry EPA- HQ - OAR2009 - 0234 - 20131) and Economic Impact Analysis for the Final Reconsideration of the Mercury and Air Toxics Standards in rulemaking docket EPA- HQ - OAR- 2009 - 0234. As noted earlier, because on an individual EGU-by-EGU basis we anticipate very similar costs, any changes to the baseline since we finalized MATS (e.g. , potential impacts of the CSAPR decision) would not impact this determination .*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **37** of **93** the supply, distribution, or use of energy. As previously stated, we believe that electric power companies would install the same or similar control technologies as they would have installed to comply with the previously finalized MATS standards. D . What are the compliance costs ? We believe there will be no sign ificant change in compliance costs as a result of this final action because electric power companies would install the same or similar control technologies as they would have installed to comply with the previously finalized MATS standards. Moreover, we fi nd no additional monitoring costs are necessary to comply with th is final action ; however, as in any other rule, EGU owners or operators may choose to conduct additional monitoring (and incur its expense) for their own purposes. E . What are the economic and employment impacts ? Because we expect that electric power companies would install the same or similar control technologies to meet the standards finalized in this action as they would have chosen to comply with the previously finalized MATS standards, we do not anticipate that this final action will result in significant changes in emissions, energy impacts, costs, benefits, or*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **38** of **93** economic impacts. Likewise, we believe this action will not have any impacts on the price of electricity, employment or labor markets, or the U . S . economy. F . What are the benefits of the final standards ? As previously stated, the EPA anticipates the power sector will not incur significant compliance cost s or savings as a result of this action and we do not anticipate any significant emission changes resulting from this action . Therefore, there are no direct monetized benefits or disbenefits associated with this action . **VIII. Statutory and Executive Order Reviews**  A. Executive Order 12866: Regulatory Planning and Review and Executive Order 13563: Improving Regulation and Regulatory Review Under Executive Order (EO) 12866 (58 FR 51735 ; October 4, 1993), this action is a “ significant regulatory action ” because it “ raises novel legal or policy issues. ” Accordingly, the EPA submitted this action to the Office of Management and Budget (OMB) for review under Executive Orders 12866 and 13563 (76 FR 3821 ; January 21, 2011) and any changes made in response to OMB recommendations have been documented in the docket for this action.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **39** of **93** In addition, the EPA prepared an analysis of the potential costs and benefits associated with this action. This analysis is contained in the “ Economic Impact Analysis for the Final Reconsideration of the Mercury and Air Toxics Standards ” found in rulemaking docket EPA- HQ - OAR- 2009 - 0234. Because our analysis shows that new electricity generating units would choose to install the same control technology in order to meet the revised emission limits as would have been necessary to meet the previously finalized MATS standards , we project that this action will result in no significant change in costs, emission reductions, or benefits. B. Paperwork Reduction Act This action does not impose any new information collection burden. Today ’ s action does not change the information collection requirements previously finalized and, as a result, does not impose any additional burden on industry. However, OMB has previously approved the information collecti on requirements contained in the existing regulations (see 77 FR 9304) under the provisions of the Paperwork Reduction Act, 44 U.S.C. 3501 et seq . and has assigned OMB control number 2060 - 0567). The OMB control numbers for EPA ’ s regulations are listed in 4 0 CFR part 9 and 48 CFR chapter 15.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **40** of **93** C. Regulatory Flexibility Act The Regulatory Flexibility Act generally requires an agency to prepare a regulatory flexibility analysis of any rule subject to notice and comment rulemaking requirements under the Administrative Procedure Act or any other statute unless the agency certifies that the rule will not have a significant economic impact on a substantial number of small entities. Small entities include small businesses, small not - for -profit enterprises, and small governmental jurisdictions. For purposes of assessing the impacts of today ’ s action on small entities, a small entity is defined as: (1) a small business as defined by the Small Business Administration ’ s (SBA) regulations at 13 CFR 121.201; (2) a small gove rnmental jurisdiction that is a government of a city, county, town, school district, or special district with a population of less that 50,000; and (3) a small organization that is any not - for profit enterprise which is independently owned and operated and is not dominant in its field. Categories and entities potentially regulated by the final rule with applicable NAICS codes are provided in the Supplementary Information section of this action. According to the SBA size standards for NAICS code 221122*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **41** of **93** Utili ties - Fossil Fuel Electric Power Generation, a firm is small if, including its affiliates, it is primarily engaged in the generation, transmission, and or distribution of electric energy for sale and its total electric output for the preceding fiscal year did not exceed 4 million MWh. After considering the economic impacts of today ’ s action on small entities, I certify that the notice will not have a significant economic impact on a substantial number of small entities. The EPA has determined that none of the small entities will experience a significant impact because the action imposes no additional regulatory requirements on owners or operators of affected sources. We have therefore concluded that today ’ s action will no t result in a significant economic impact on a substantial number of small entit ies. D. Unfunded Mandates Reform Act This action contains no Federal mandates under the provisions of Title II of the Unfunded Mandates Reform Act of 1995 (UMRA), 2 U.S.C. 1531 - 1538 for State, local, or tribal governments or the private sector. The action imposes no enforceable duty on any State, local, or tribal governments or the private sector. Therefore, this action is not subject to the*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **42** of **93** requirements of UMRA sections 202 or 205. This action is also not subject to the requirements of UMRA section 203 because it contains no regulatory requirements that might significantly or uniquely affect small governments because it contains no requirements that apply to such governments or impose obligations upon them. E. Executive Order 13132: Federalism This action does not have federalism implications. It will not have substantial direct effects on the states, on the relationship between the national government and the states, or on the distribution of power and responsibilities among the various levels of government, as specified in EO 13132. None of the affected facilities are owned or operated by state governments, and the requirements discussed in today ’ s notice will not supersede stat e regulations that are more stringent. Thus, EO 13132 does not apply to today ’ s notice of reconsideration. F. Executive Order 13175: Consultation and Coordination with Indian Tribal Governments This action does not have tribal implications. It will not have substantial direct effects on tribal governments, on the relationship between the Federal government and Indian tribes,*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **43** of **93** or on the distribution of power and responsibilities between the Federal government and Indian tribes, as specified in EO 13175. No af fected facilities are owned or operated by Indian tribal governments. Thus, EO 13175 does not apply to today ’ s action. G. Executive Order 13045: Protection of Children from Environmental Health Risks and Safety Risks This action is not subject to EO 13045 (62 FR 19885 ; April 23, 1997) because it is not economically significant as defined in EO 12866. The EPA has evaluated the environmental health or safety effects of the final MATS on children. The results of the evaluation are discussed in that final rule (77 FR 9304; February 16, 2012) and are contained in rulemaking docket EPAHQ - OAR- 2009 - 0234. H. Executive Order 13211: Actions that Significantly Affect Energy Supply, Distribution, or Use This action is not a “ significant energy action ” as defined in EO 13211 (66 FR 28355; May 22, 2001) because it is not likely to have a significant adverse effect on the supply, distribution, or use of energy. Further, we conclude that today ’ s action is not likely to have any adverse energy effects becau se it is not expected to impose any additional regulatory requirements on the owners of affected facilities.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **44** of **93** I. National Technology Transfer and Advancement Act Section 12(d) of the National Technology Transfer and Advancement Act (NTTAA) of 1995 (Public Law 104 - 113; 15 U.S.C. 272 note) directs EPA to use voluntary consensus standards in their regulatory and procurement activities unless to do so would be inconsistent with applicable law or otherwise impracticable. Voluntary consensus standards are technica l standards (e.g., material specifications, test methods, sampling procedures, business practices) developed or adopted by one or more voluntary consensus bodies. The NTTAA requires EPA to provide Congress, through the OMB, with explanations when EPA decides not to use available and applicable voluntary consensus standards. During the development of the final MATS rule, the EPA searched for voluntary consensus standards that might be applicable. The search identified three voluntary consensus standards that were considered practical alternatives to the specified EPA test methods. An assessment of these and other voluntary consensus standards is presented in the preamble to the final MATS rule (77 FR 9441; February 16, 2012). Today ’ s action does not make use of any additional technical standards beyond those cited in the final MATS rule. Therefore, the EPA is*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **45** of **93** not considering the use of any additional voluntary consensus standards for this action . J. Executive Order 12898: Federal Actions to Address Environmental Justice in Minority Populations and Low- income Populations Executive Order 12898 (59 FR 7629 ; Feb ruary 16, 1994) establishes federal executive policy on environmental justice. Its main provision directs federal agencies, to the greatest extent practicable and permitted by law, to make environmental justice part of their mission by identifying and addressing, as appropriate, disproportionately high and adverse human health or environmental effects of their programs, policies, and activities on minority populations and low- income populations in the United States. The EPA has determined that this action will not have disproportionately high and adverse human health or environmental effects on minority or low- income populations because it does not affect the level of protection provided to human health or the environment. Our analysis shows that new EGUs would choose to install the same control technology in order to meet the revised emission limits as would have been necessary to meet the previously finalized standard. Under the*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **46** of **93** relevant assumptions, we project that this action will result in
no significant change in emission reductions. K. Congressional Review Act The Congressional Review Act, 5 U.S.C. 801 et seq., as added by the Small Business Regulatory Enforcement Fairness Act of 1996, generally provides that before a rule may take effect, the agency promulgating the rule must submit a rule report, which includes a copy of the rule, to each House of the Congress and to the Comptroller General of the United States. The EPA will submit a report containing this final action and other required information to the U.S. Senate, the U.S. House of Representatives, and the Comptroller General of the United States prior to publication of the rule in the Federal Register . A major rule cannot take effect until 60 days after it is published in the Federal Register . This act ion is not a “major rule ” as defined by 5 U.S.C. 804(2). This rule will be effective **[INSERT DATE 60 DAYS AFTER DATE OF PUBLICATION IN THE FEDERAL REGISTER]**  .*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **47** of **93** List of Subjects in 40 CFR Parts 60 and 63 Environmental protection, Administrative practice and procedure, Air pollution control, Hazardous substances, Intergovernmental relations, Reporting and recordkeeping requirements.

Dated:

______________ , Bob Perciasepe Acting Administrator.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **48** of **93** For the reasons discussed in the preamble, 40 CFR parts 60 and 63 are amended to read as follows: PART 60 -- STANDARDS OF PERFORMANCE FOR NEW STATIONARY SOURCES 1. The authority citation for part 60 continues to read as follows: Authority: 42 U.S.C. 7401 et seq . 2. Amend § 60.41Da by revising the definitions of “ coal ” and

“ integrated gasification combined cycle electric utility steam generating unit, ” and by adding the definition of “ natural gas ” in alphabetical order to read as follows: **§ 60.41Da Definitions.**  * * * * * Coal means all solid fuels classified as anthracite, bituminous, subbituminous, or lignite by the American Society of Testing and Materials in ASTM D388 (incorporated by reference, see §60.17) and coal refuse. Synthetic fuels derived from coal for the purpose of creating useful heat, including but not limited to solvent - refined coal, gasified coal, coal - oil mixtures, and coal -water mixtures are included in this definition for the purposes of this subpart. * * * * * Integrated gasification combined cycle electric utility steam*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **49** of **93** generating unit or IGCC electric utility steam generating unit means an electric utility combi ned cycle gas turbine that is designed to burn fuels containing 50 percent (by heat input) or more solid- derived fuel not meeting the definition of natural gas. The Administrator may waive the 50 percent solid- derived fuel requirement during periods of the gasification system construction , startup and commissioning, shutdown, or repair. No solid fuel is directly burned in the unit during operation. * * * * * Natural gas means a fluid mixture of hydrocarbons (e.g., methane, ethane, or propane), composed of at least 70 percent methane by volume or that has a gross calorific value between 35 and 41 megajoules (MJ) per dry standard cubic meter (950 and 1,100 Btu per dry standard cubic foot), that maintains a gaseous state under ISO conditions. In addition, natural gas contains 20.0 grains or less of total sulfur per 100 standard cubic feet. Finally, natural gas does not include the following gaseous fuels: landfill gas, diges ter gas, refinery gas, sour gas, blast furnace gas, coal - derived gas, producer gas, coke oven gas, or any gaseous fuel produced in a process which might result in highly variable sulfur content or heating value. * * * * **** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **50** of **93** 3. Amend § 60.42Da by revising paragraphs (a) , (b)(2), and (e)(1) to read as follows : **§ 60.42Da Standards for particulate matter (PM).**  (a) Except as provided in paragraph (f) of this section, on and after the date on which the initial performance test is completed or required to be completed under §60.8, whichever date comes first, an owner or operator of an affected facility shall not cause to be discharged into the atmosphere from any affected facility for which construction, reconstruction, or modification commenced before March 1, 2 005, any gases that contain PM in excess of 13 ng/J (0.03 lb/MMBtu) heat input. (b) * * * (2) An owner or operator of an affected facility that combusts only natural gas and/or synthetic natural gas that chemically meets the definition of natural gas is exempt from the opacity standard specified in paragraph (b) of this section. * * * * * (e) * * * (1) On and after the date on which the initial performance test is completed or required to be completed under §60.8, whichever date comes first, the owner or operator shall not cause to be discharged into the atmosphere from that affected facility any*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **51** of **93** gases that contain PM in excess of the applicable emissions limit specified in paragraphs (e)(1)(i) or (ii) of this section. (i) For an affected facilit y which commenced construction or reconstruction: (A) 11 ng/J (0.090 lb/MWh) gross energy output; or (B) 12 ng/J (0.097 lb/MWh) net energy output. * * * * * ( ii) For an affected facility which commenced modification, the emission limits specified in paragraphs (c) or (d) of this section. * * * * * 4 . Amend **§** 60.48Da by revising paragraphs (f), (o) introductory text , (o)(1), (o)(2) introductory text, (o)(3) introductory text, (o)(3)(i), and (o)(4) introductory text to read as follows: **§ 60.48Da**  **Compliance provisions.** * * * * * ( f) For affected facilities for which construction, modification, or reconstruction commenced before May 4, 2011, compliance with the applicable daily average PM emissions limit is determined by calculating the arithmet ic average of all hourly emission rates each boiler operating day, except for data*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **52** of **93** obtained during startup, shutdown, or malfunction periods. Daily averages are only calculated for boiler operating days that have out - of - control periods totaling no more than 6 hours of unit operation during which the standard applies. For affected facilities for which construction or reconstruction commenced after May 3, 2011, that elect to demonstrate compliance using PM CEMS , compliance with the applicable PM emissions limit in §60.42Da is determined on a 30 -boiler operating day rolling average basis by calculating the arithmetic average of all hourly PM emission rates for the 30 successive boiler operating days, except for data obtained during periods of startup or shutdown. * * * * * ( o) Compliance provisions for sources subject to §60.42Da(c)(2), (d), or (e)(1)(ii) . Except as provided for in paragraph (p) of this section, the owner or operator must demonstrate compliance with each applicable emission s limit according to the requirements in paragraphs (o)(1) through (o)(5) of this section. (1) You must conduct a performance test to demonstrate initial compliance with the applicable PM emissions limit in §60.42Da by the applicable date specified in §60.8(a). There after, you must*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **53** of **93** conduct each subsequent performance test within 12 calendar months following the date the previous performance test was required to be conducted. You must conduct each performance test according to the requirements in §60.8 using the test methods and procedures in §60.50Da. The owner or operator of an affected facility that has not operated for 60 consecutive calendar days prior to the date that the subsequent performance test would have been required had the unit been operating is not requi red to perform the subsequent performance test until 30 calendar days after the next boiler operating day. Requests for additional 30 day extensions shall be granted by the relevant air division or office director of the appropriate Regional Office of the U.S. EPA. (2) You must monitor the performance of each electrostatic precipitator or fabric filter (baghouse) operated to comply with the applicable PM emissions limit in §60.42Da using a continuous opacity monitoring system (COMS) according to the requirements in paragraphs (o)(2)(i) through (vi) unless you elect to comply with one of the alternatives provided in paragraphs (o)(3) and (o)(4) of this section, as applicable to your control device. * * * * * (3) As an alternative to complying with the requirements of*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **54** of **93** paragraph (o)(2) of this section, an owner or operator may elect to monitor the performance of an electrostatic precipitator (ESP) operated to comply with the applicable PM emissions limit in §60.42Da using an ESP predictive model developed in accordance with the requirements in paragraphs (o)(3)(i) through (v) of this section. (i) You must calibrate the ESP predictive model with each PM control device used to comply with the applicable PM emissions limit in §60.42Da operating under normal conditions. In cases when a wet scrubber is used in combination with an ESP to comply with the PM emissions limit, the wet scrubber must be maintained and operated. * * * * * (4) As an alternative to complying with the requirements of paragraph (o)(2) of this section, an owner or operator may elect to monitor the performance of a fabric filter (baghouse) operated to comply with the applicable PM emissions limit in §60.42Da by using a bag leak detection system according to the requirements in paragraphs (o)( 4)(i) through (v) of this section. * * * * * 5 . Amend § 6 0 .49Da by:*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **55** of **93** a. Revising paragraphs (a) introductory text; b. Adding paragraph (a)(3) ( iv); and c. Revising paragraphs (a)(4) , (b) introductory text, and (t) . The revised and added text reads as follows: **§ 60.49Da Emission monitoring.**  (a) An owner or operator of an affected facility subject to the opacity standard in §60.42Da must monitor the opacity of emissions discharged from the affected facility to the atmosphere according to the applicable requirements in paragraphs (a)(1) through (4) of this section. * * * * * ( 3 ) * * * (iv) If the maximum 6 -minute opacity is less than 10 percent during the most recent Method 9 of appendix A

– 4 of this part performance test, the owner or operator may, as an alternative to performing subsequent Method 9 of appendix A

– 4 performance tests, el ect to perform subsequent monitoring using a digital opacity compliance system according to a site - specific monitoring plan approved by the Administrator. The observations must be similar, but not necessarily identical, to the requirements in paragraph (a) (3)(iii) of this section. For reference purposes in preparing the monitoring plan, see OAQPS*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **56** of **93** “ Determination of Visible Emission Opacity from Stationary Sources Using Computer -Based Photographic Analysis Systems. ” This document is available from the U.S. Environmental Protection Agency (U.S. EPA); Office of Air Quality and Planning Standards; Sector Policies and Programs Division; Measurement Policy Group (D243

– 02), Research Triangle Park, NC 27711. This document is also available on the Technology Transfer Network (TTN) under Emission Measurement Center Preliminary Methods. * * * * * (4) An owner or operator of an affected facility that is subject to an opacity standard under §60.42Da is not required to operate a COMS provided that affected facility meet s the conditions in either paragraph (a)(4)(i) or (ii) of this section. (i) The affected facility combusts only gaseous and/or liquid fuels (excluding residue oil) where the potential SO 2 emissions rate of each fuel is no greater than 26 ng/J (0.060 lb/MMBtu), and the unit operates according to a written site - specific monitoring plan approved by the permitting authority. This monitoring plan must include procedures and criteria for establishing and monitoring specific parameters for the affected facility i ndicative of compliance with the opacity standard. For testing performed as part of this site - specific monitoring plan,*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **57** of **93** the permitting authority may require as an alternative to the notification and reporting requirements specified in §§60.8 and 60.11 that the owner or operator submit any deviations with the excess emissions report required under §60.51Da(d). (ii) The owner or operator of the affected facility installs, calibrates, operates, and maintains a particulate matter continuous parametric monitoring system (PM CPMS) according to the requirements specified in subpart UUUUU of part 63. * * * * * ( b) The owner or operator of an affected facility must install, calibrate, maintain, and operate a CEMS, and record the output of the system, for measuring SO 2 emissions, except where only gaseous and/or liquid fuels (excluding residual oil) where the potential SO 2 emissions rate of each fuel is 26 ng/J (0.060 lb/MMBtu) or less are combusted, as follows: * * * * * ( t) The owner or operator of an affected facility demonstrating compliance with the output -based emissions limit under §60.42Da must either install, certify, operate, and maintain a CEMS for measuring PM emissions according to the requirements of paragraph (v) of this section or install , calibrate, operate, and maintain a PM CPMS according to the requirements for new*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **58** of **93** facilities specified in subpart UUUUU of part 63 of this chapter . An owner or operator of an affected facility demonstrating compliance with the input -based emissions limit in §60.42Da may install, certify, operate, and maintain a CEMS for measuring PM emissions according to the requirements of paragraph (v) of this section. * * * * * 6 . Revise § 6 0 .50Da paragraph (f) to read as follows: **§ 60.50Da Compliance determination**  **procedures and methods.** * * * * * (f) The owner or operator of an electric utility combined cycle gas turbine that does not meet the definition of an IGCC must conduct performance test s for PM, SO 2 , and NOX using the procedures of Method 19 of appendi x A
– 7 of this part. The SO 2 and NOX emission rates calculations from the gas turbine used in Method 19 of appendix A

– 7 of this part are determined when the gas turbine is performance tested under subpart GG of this part. The potential uncontrolled PM emiss ion rate from a gas turbine is defined as 17 ng/J (0.04 lb/MMBtu) heat input. * * * * * PART 63

—NATIONAL EMISSION STANDARDS FOR HAZARDOUS AIR POLLUTANTS FOR SOURCE CATEGORIES*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **59** of **93** 7 . The authority citation for 40 CFR Part 63 continues to read as follows: Authority : 42 U.S.C. 7401, et seq . 8 . In **§** 63.9982 , revise paragraphs (a) introductory text, (b), and (c) to read as follows: **§ 63.9982 What is the affected source of this subpart?**  (a) This subpart applies to each individual or group of two or more new, reconstructed, or existing affected source(s) as described in paragraphs (a)(1) and (2) of this section within a contiguous area and under common control. * * * * * (b) An EGU is new if you commence construction of the coal - or oil - fired EGU after May 3 , 2011. (c) An EGU is reconstructed if you meet the reconstruction criteria as defined in §63.2, and if you commence reconstruction after May 3, 2011. * * * * * 9 . In § 63.100 00, revise paragraph s ( c )( 1 ) (iv) and (c)(2)(ii) to read as follows: **§ 63.1000**  **0 What are my general requirements for complying with**  **this subpart?**  * * * * **** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **60** of **93** (c) * * * (1) * * * (iv) If your coal - fired or solid oil derived fuel - fired EGU or IGCC EGU does not qualify as a LEE for total non -mercury HAP metals, individual non -mercury HAP metals, or filterable particulate matter (PM), you must demonstrate compliance through
an initial performance test and you must monitor continuous performance through either use of a particulate matter continuous parametric monitoring system (PM CPMS), a PM CEMS, or , for an existing EGU, compliance performance testing repeated quarterly. * * * * * (c) * * * (2) * * * ( ii) If your liquid oil - fired unit does not qualify as a LEE for total HAP metals (including mercury), individual metals (including mercury), or filterable PM you must demonstrate compliance through an initial performance test and you must monitor continuous performance through either use of a PM CPMS, a PM CEMS, or , for an existing EGU, performance testing conducted quarter ly. * * * * **** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **61** of **93** 1 0 . Amend § 63.10005 by: a. Revis ing paragraphs (d)(2)(ii) and (i)(4)(ii) ; b. Adding paragraph (i)(5) and (i)(6) . The revised and added text read as follows: **§ 63.10005 What are my initial compliance requirements and by**  **what date must I conduct them?**  * * * * * (d) * * * (2) * * * ( ii) You must demonstrate continuous compliance with the PM CPMS site - specific operating limit that corresponds to the results of the performance test demonstrating compliance with the emission limit with which you choose to comply . * * * * * ( i) * * * (4) * * * (ii) ASTM D4006 - 11 , “ Standard Test Method for Water in Crude Oil by Distillation, ” including Annex A1 and Appendix A1. * * * * * (5) Use one of the following methods to obtain fuel moisture samples: (i) ASTM D4177 - 95 (Reapproved 2010) , “ Standard Practice for*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **6 2**  of **93** Automatic Sampling of Petroleum and Petroleum Products, ” including Annexes A1 through A6 and Appendices X1 and X2, or (ii) ASTM D4057 - 06 (Reapproved 2011), “ Standard Practice for Manual Sampling of Petroleum and Petroleum Products, ” including Annex A1. (6) Should the moisture in your liquid fuel be more than 1.0 percent by weight, you must (i) Conduct HCl and HF emissions testing quarterly (and monitor site - specific operating parameters as provided in §63.10000(c)(2)(iii) or (ii) Use an HCl CEMS and/or HF CEMS. * * * * * 1 1 . In § 63.10006 , revise paragraph (c) to read as follows: **§ 63.10006 When must I conduct subsequent performance tests or**  **tune -** **ups?** * * * * * (c) Except where paragraphs (a) or (b) of this section apply, or where you install, certify, and operate a PM CEMS to demonstrate compliance with a filterable PM emissions limit, for liquid oil - , solid oil - derived fuel - , coal - fired and IGCC EGUs, you must conduct all applicable periodic emissions tests for filterable PM, individual , or total HAP metals emissions according to Table*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **63** of **93** 5 to this subpart, §63.10007, and §63.10000(c), except as otherwise provided in §63.10021(d)(1). * * * * * 1 2 . In § 63.10007 , revise paragraph (c) to read as follows: **§ 63.10007 What methods and other procedures must I use for the**  **performance tests?** * * * * * (c) If you choose the filterable PM method to comply with the PM emission limit and demonstrate continuous performance using a PM CPMS as provided for in §63.10000(c), you must also establish an operating limit according to §63.10011(b), §63.10023, and Tables 4 and 6 to this subpart. Should you desire to have operating limits that correspond to loads other than maximum normal ope rating load, you must conduct testing at those other loads to determine the additional operating limits. * * * * * 1 3 . In § 63.10009 , revise paragraphs (b)(2) and (b)(3) to read as follows: **§ 63.10009 May I use emissions averaging to comply with this**  **s ubpart?**  * * * * * (b) * * **** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **64** of **93** (2) Weighted 30 -boiler operating day rolling average emissions rate equations for pollutants other than Hg. Use equation 2a or 2b to calculate the 30 day rolling average emissions daily.

= ∑ [∑ ( × )] + ∑ ( × )

∑ [∑ ( )] + ∑ ( . 2 )

Where: Her i = hourly emission rate (e.g., lb/MMBtu, lb/MWh) from unit i ’ s CEMS for the preceding 30 - group boiler operating days, Rmi = hourly heat input or gross electrical output from unit i for the preceding 30 - group boiler operating days, p = number of EGUs in emissions averaging group that rely on CEMS or sorbent trap monitoring, n = number of hourly rates collected over 30 - group boiler operating days, Ter i = Emissions rate from most recent emissions test of unit i in terms of lb/heat input or lb/gross electrical output, Rt i = Total heat input or gross electrical output of unit i for the preceding 30 -boiler operating days, and
m = number of EGUs in emissions averaging group that rely on emissions testing.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **65** of **93** = ∑ [∑ ( × × )] + ∑ ( × × )

∑ [∑ ( × )] + ∑ × (
. 2 )

Where: variables with similar names share the descriptions for Equation 2a, Smi = steam generation in units of pounds from unit i that uses CEMS for the preceding 30 - group boiler operating days, Cfmi = conversion factor, calculated from the most recent compliance test results, in units of heat input per pound of steam generated or gross electrical output per pound of steam generated, from unit i that uses CEMS from the preceding 30 group boiler operating days, St i = steam generation in units of pounds from unit i that uses emissions testing, and Cft i = conversion factor, calculated from the most recent compliance test results, in units of heat input per pound of steam generated or gross electrical output per pound of steam generated, from unit i that uses emissions testing. * * * * * (3) Weighted 90 -boiler operating day rolling average emissions rate equations for Hg emissions from EGUs in the “ coal - fired unit not low rank virgin coal ” subcategory. Use equation 3a or*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **66** of **93** 3b to calculate the 90 - day rolling average emissions daily.

= ∑ [∑ ( × )] + ∑ ( × )

∑ [∑ ( )] + ∑ ( . 3 )

Where: Her i = hourly emission rate from unit i ’ s CEMS or Hg sorbent trap monitoring system for the preceding 90 - group boiler operating days, Rmi = hourly heat input or gross electrical output from unit i for the preceding 90 - group boiler operating days, p = number of EGUs in emissions averaging group that rely on CEMS, n = number of hourly rates collected over the 90 - group boiler operating days, Ter i = Emissions rate from most recent emissions test of unit i in terms of lb/heat input or lb/gross electrical output, Rt i = Total heat input or gross electrical output of unit i for the preceding 90 -boiler operating days, and m = number of EGUs in emissions averaging group that rely on emissions testing.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **67** of **93** = ∑ [∑ ( × × )] + ∑ ( × × )

∑ [∑ ( × )] + ∑ × (
. 3 )

Where: variables with similar names share the descriptions for Equation 2a, Smi = steam generation in units of pounds from unit i that uses CEMS or a Hg sorbent trap monitoring for the preceding 90 - group boiler operating days, Cfmi = conversion factor, calculated from the most recent compliance test results, in units of heat input per pound of steam generated or gross electrical output per pound of steam generated, from unit i that uses CEMS or sorbent trap monitoring from the prece ding 90 - group boiler operating days, St i = steam generation in units of pounds from unit i that uses emissions testing, and Cft i = conversion factor, calculated from the most recent emissions test results, in units of heat input per pound of steam generated or gross electrical output per pound of steam generated, from unit i that uses emissions testing. * * * * * 1 4 . In § 63.10010 , revise paragraph (j)(1)(i) to read as follows:*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **68** of **93 §**  **63.10010 What are my monitoring, installation, operation, and maintenance**  **requirements?** * * * * * (j) * * * (1) * * * (i) Install and certify your HAP metals CEMS according to the procedures and requirements in your approved site - specific test plan as required in §63.7(e). The reportable measurement output from the HAP metals CEMS must be expressed in units of the applicable emissions limit ( e.g. , lb/MMBtu, lb/MWh) and in the form of a 30 -boiler operating day rolling average. * * * * * 1 5 . Amend § 63.1002 1 by adding paragraphs ( c )(1) and (2) to read as follows: **§ 63**  **.10021 How do I demonstrate continuous compliance with the emission limitations, operating limits, and work practice**  **standards?** * * * * * ( c ) * * * ( 1 ) For any exceedance of the 30 -boiler operating day PM CPMS average value from the established operating parameter limit for an EGU subject to the emissions limits in Table 1 to this*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **69** of **93** subpart , you must: (i) Within 48 hours of the exceedance , visually inspect the air pollution control device (APCD); (ii) If the inspection of the APCD identifies the cause of the exceedance , take corrective action as soon as possible, and return the PM CPMS measurement to within the established value; and (iii) Within 45 days of the exceedance or at the time of the annual compliance test, whichever comes first, conduct a PM emissions compliance test to determine compliance with the PM emissions limit and to verify or re - establish the CPMS operating limit. You are not required to conduct any additional testing for any exceedance s that occur between the time of the original exceedance and the PM emissions compliance test required under this paragraph. (2) PM CPMS exceedance s of the operating limit for an EGU subject to the emissions limits in Table 1 of this subpart leading to more than four required performance tests in a 12 - month period (rolling monthly) constitute a separate violation of this subpart. * * * * * 1 6 . In § 63.10023 , revise paragraph (b) to read as follows:*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **70** of **93 §**  **63.10023 How do I establish my PM CPMS operating limit and**  **determine compliance with it?** * * * * * (b) Determine your operating limit as provided in paragraph (b)(1) or (b)(2) of this section. You must verify an existing or establish a new operating limit after each repeated performance test. (1) For an existing EGU , determine your operating limit based on the highest 1 -hour average PM CPMS output value recorded during the performance test. (2) For a new EGU, determine your operating limit as follows. (i) If your PM performance test demonstrates your PM emissions do not exceed 75 percent of your emissions limit, you will use the average PM CPMS value recorded during the PM compliance test, the milliamp equivalent of zero output from your PM CPMS, and the average PM result of your compliance test to establish your operating limit. Calculate the operating limit by establishing a relationship of PM CPMS signal to PM concentration using the PM CPMS instrument zero, the average PM CPMS values corresponding to the three complian ce test runs, and the average PM concentration from the Method 5 compliance test with the procedures in (b)(2)(i)(A) through (D) of this section.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **71** of **93** (A) Determine your PM CPMS instrument zero output with one of the following procedures. ( 1 ) Zero point data for in - situ instruments should be obtained by removing the instrument from the stack and monitoring ambient air on a test bench. ( 2 ) Zero point data for extractive instruments should be obtained by removing the extractive probe from the stack and drawing i n clean ambient air. ( 3 ) The zero point can also can be obtained by performing manual reference method measurements when the flue gas is free of PM emissions or contains very low PM concentrations (e.g., when your process is not operating, but the fans are operating or your source is combusting only natural gas) and plotting these with the compliance data to find the zero intercept. ( 4 ) If none of the steps in paragraphs (A) ( 1 ) through ( 3 ) of this section are possible, you must use a zero output value provi ded by the manufacturer. (B) Determine your PM CPMS instrument average ( ) in milliamps, and the average of your corresponding three PM compliance test
runs ( ) , using equation 10.



## ̅ = ∑ , = ∑ (Eq. 10)*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **72** of **93** Where : X i = the PM CPMS data points for run i of the performance test, Y i = the PM emissions value (in lb/MWh) for run i of the performance test, and n = the number of data points. (C) With your PM CPMS instrument zero expressed in milliamps, your three run average PM CPMS milliamp value, and your three
run average PM emissions value (in lb/MWh) from your compliance runs, determine a relationship of PM lb/MWh per milliamp with equation 11.



## = ( ̅ ) (Eq. 11)
Where: R = the rel ative PM lb/MWh per milliamp for your PM CPMS, = the three run average PM lb/MWh,

̅ = the three run average milliamp output from you r PM CPMS, and z = the milliamp equivalent of your instrument zero determined from (b)(2) (i)(A) of this section . (D) Determine your source specific 30 - day rolling average operating limit using the PM lb/MWh per milliamp value from equation 11 in equation 12, below. This sets your operating*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **73** of **93** limit at the PM CPMS output value corresponding to 75 percent of your emission limit.



## = + (
. × ) (Eq. 12)

Where: O L = the operating limit for your PM CPMS on a 30 - day rolling average, in milliamps , L = your source PM emissions limit in lb/MWh, z = your instrument zero in milliamps, determined from (b)(2) (i)(A) of this section , and R = the relative PM lb/MWh per milliamp for your PM CPMS, from equation 11. (ii) If your PM compliance test demonstrates your PM emissions exceed 75 percent of your emissions limit, you will use the average PM CPMS value recorded duri ng the PM compliance test demonstrating compliance with the PM limit to establish your operating limit. (A) Determine your operating limit by averaging the PM CPMS milliamp output corresponding to your three PM performance test runs that demonstrate compli ance with the emission limit using*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **74** of **93** equation 13.



## = ∑ (Eq. 13)

Where: X i = the PM C PMS data points for all runs i, n = the number of data points, and Oh = your site specific operating limit, in milliamps. (iii) Your PM CPMS must provide a 4 - 20 milliamp output and the establishment of its relationship to manual reference method measurements must be determined in units of milliamps. (iv) Your PM CPMS operating range must be capable of reading PM concentrations from zero to a level e quivalent to two times your allowable emission limit. If your PM CPMS is an auto - ranging instrument capable of multiple scales, the primary range of the instrument must be capable of reading PM concentration from zero to a level equivalent to two times you r allowable emission limit. (v) During the initial performance test or any such subsequent performance test that demonstrates compliance with the PM limit, record and average all milliamp output values from the PM CPMS*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **75** of **93** for the periods corresponding to the compliance test runs. (vi) For PM performance test reports used to set a PM CPMS operating limit, the electronic submission of the test report must also include the make and model of the PM CPMS instrument, serial number of the instrument, analytical princ iple of the instrument (e.g. beta attenuation), span of the instruments primary analytical range, milliamp value equivalent to the instrument zero output, technique by which this zero value was determined, and the average milliamp signal corresponding to
e ach PM compliance test run. * * * * * 1 7 . In § 63.10030 , revise paragraphs (b), (c), and (d) to read as follows: **§ 63.10030 What notifications must I submit and when?**  * * * * * (b) As specified in §63.9(b)(2), if you startup your EGU that is an affected source before April 16, 2012 , you must submit an Initial Notification not later than 120 days after April 16, 2012. (c) As specified in §63.9(b)(4) and (b)(5), if you startup your new or reconstructed EGU that is an affected source on or after April 16, 2012, you must submit an Initial Notification not*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **76** of **93** later than 15 days after the actual date of startup of the EGU that is an affected source. (d) When you are required to conduct a performance test, you must submit a Notification of Intent to conduct a performance test at least 3 0 days before the performance test is scheduled to begin. * * * * * 18 . Amend § 63.10042 by revising the definition of “ Unit designed for coal > 8,300 Btu/lb subcategory” t o read as follows: **§ 63.10042 What definitions apply to this subpart?**  * * * * * Unit designed for coal ≥ 8,300 Btu/lb subcategory means any coal - fired EGU that is not a coal - fired EGU in the “ unit designed for low rank virgin coal ” subcategory. * * * * * 19 . Revise Table 1 to Subpart UUUUU of Part 63 to read as follows: **Table 1 to Subpart UUUUU of Part 63 —**  **Emission Limits for New or Reconstructed EGUs**  As stated in §63.9991, you must comply with the following

applicable emission limits: **If your EGU For the following**  **You must meet the Using these** *** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **77** of **93 is in this**  **subcategory**

**... pollutants ...**  **following emission limits and work**  **practice standards**

**... requirements,**  **as appropriate (e.g.,**  **specified sampling**  **volume or test run duration)**  **an d**  **limitations with the test**  **methods in Table 5...**  1. Coal - fired unit not low rank virgin coal. a. Filterable

particulate matter (PM) 9.0E - 2 lb/MWh 1 Collect a minimum of 4 dscm per run. OR OR Total non - Hg HAP metals 6.0E - 2 lb/GWh Collect a minimum of 4 dscm per run. OR OR Individual HAP metals: Antimony (Sb) Arsenic (As) Beryllium (Be) Cadmium (Cd) Chromium (Cr) Cobalt (Co) Lead (Pb) Manganese (Mn) Nickel (Ni) Selenium (Se) 8.0E - 3 lb/GWh 3.0E - 3 lb/GWh 6.0E - 4 lb/GWh 4.0E - 4 lb/GWh 7.0E - 3 lb/GWh 2.0E - 3 lb/GWh 2 .0E - 2 lb/GWh 4.0E - 3 lb/GWh 4.0E - 2 lb/GWh 5.0E - 2 lb/GWh Collect a minimum of 3 dscm per run.

b. Hydrogen chloride (HCl) 1.0E - 2 lb/MWh For Method 26A, collect a minimum of 3 dscm per run. For ASTM D6348 - 03 2 or Method 320, sample for a minimum of 1*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **78** of **93** hour. OR Sulfur dioxide (SO 2 ) 3 1 .0 lb/MWh SO 2 CEMS. c. Mercury (Hg) 3.0E - 3 lb/GWh Hg CEMS or sorbent trap monitoring system only. 2. Coal - fired units low rank virgin coal. a. Filterable

particulate matter (PM) 9.0E - 2 lb/MWh 1 Collect a minimum of 4 dscm per run. OR OR Total non - Hg HAP metals 6.0E - 2 lb/GWh Collect a minimum of 4 dscm per run. OR OR Individual HAP metals: Antimony (Sb) Arsenic (As) Beryllium (Be) Cadmium (Cd) Chromium (Cr) Cobalt (Co) Lead (Pb) Manganese (Mn) Nickel (Ni) Selenium (Se) 8.0E - 3 lb/GWh 3.0E - 3 lb/GWh 6.0E - 4 lb/GWh 4.0E - 4 lb/GWh 7.0E - 3 lb/GWh 2.0E - 3 lb/GWh 2 .0E - 2 lb/GWh 4.0E - 3 lb/GWh 4.0E - 2 lb/GWh 5.0E - 2 lb/GWh Collect a minimum of 3 dscm per run.

b. Hydrogen chloride (HCl) 1.0E - 2 lb/MWh For Method 26A, collect a minimum of 3 dscm per run. For ASTM D6348 - 03 2 or Method 320, sample for a minimum of 1 hour. OR Sulfur dioxide 1.0 lb/MWh SO 2 CEMS.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **79** of **93** (SO 2 ) 3 c. Mercury (Hg) 4.0E - 2 lb/GWh Hg CEMS or sorbent trap monitoring system only. 3. IGCC unit. a. Filterable

particulate matter (PM) 7.0E - 2 lb/MWh 4 9.0E - 2 lb/MWh 5 Collect a minimum of 1 dscm per run. OR OR Total non - Hg HAP metals 4.0E - 1 lb/GWh Collect a minimum of 1 dscm per run. OR OR Individual HAP metals: Antimony (Sb) Arsenic (As) Beryllium (Be) Cadmium (Cd) Chromium (Cr) Cobalt (Co) Lead (Pb) Manganese (Mn) Nickel (Ni) Selenium (Se) 2.0E - 2 lb/GWh 2.0E - 2 lb/GWh 1.0E - 3 lb/GWh 2.0E - 3 lb/GWh 4.0E - 2 lb/GWh 4.0E - 3 lb/GWh 9.0E - 3 lb/GWh 2.0E - 2 lb/GWh 7.0E - 2 lb/GWh 3.0E - 1 lb/GWh Collect a minimum of 2 dscm per run.

b. Hydrogen chloride (HCl) 2.0E - 3 lb/MWh For Method 26A, collect a minimum of 1 dscm per run; for Method 26, collect a minimum of 120 liters per run. For ASTM D6348 - 03 2 or Method 320, sample for a minimum of 1 hour. OR*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **80** of **93** Sulfur dioxide (SO 2 ) 3 4.0E - 1 lb/MWh SO 2 CEMS. c. Mercury (Hg) 3.0E - 3 lb/GWh Hg CEMS or sorbent trap monitoring system only. 4. Liquid oil - fired unit

– continental (excluding limited-use liquid oil fired subcategory units). a. Filterable

particulate matter (PM) 3 .0E - 1 lb/MWh 1 Collect a minimum of 1 dscm per run. OR OR Total HAP metals 2.0E - 4 lb/MWh Collect a minimum of 2 dscm per run. OR OR Individual HAP metals: Antimony (Sb) Arsenic (As) Beryllium (Be) Cadmium (Cd) Chromium (Cr) Cobalt (Co) Lead (Pb) Manganese (Mn) Nickel (Ni) Selenium (Se) 1.0E - 2 lb/GWh 3.0E - 3 lb/GWh 5.0E - 4 lb/GWh 2.0E - 4 lb/GWh 2.0E - 2 lb/GWh 3.0E - 2 lb/GWh 8.0E - 3 lb/GWh 2.0E - 2 lb/GWh 9.0E - 2 lb/GWh 2.0E - 2 lb/GWh Collect a minimum of 2 dscm per run.

Mercury (Hg) 1.0E - 4 lb/GWh For Method 30B sample volume determination (Section 8.2.4), the estimated Hg concentration should nominally be < 1⁄2 the standard. b. Hydrogen chloride (HCl) 4 .0E - 4 lb/MWh For Method 26A, collect a minimum of 3 dscm per run.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **81** of **93** For ASTM D6348 - 03 2 or Method 320, sample for a minimum of 1 hour. c. Hydrogen fluoride (HF) 4 .0E - 4 lb/MWh For Method 26A, collect a minimum of 3 dscm per run. For ASTM D6348 - 03 2 or Method 320, sample for a minimum of 1 hour. 5. Liquid oil - fired unit

– non continental (excluding limited-use liquid oil fired subcategory units). a. Filterable

particulate matter (PM) 2.0E - 1 lb/MWh 1 Collect a minimum of 1 dscm per run. OR OR Total HAP metals 7.0E - 3 lb/MWh Collect a minimum of 1 dscm per run. OR OR Individual HAP metals: Antimony (Sb) Arsenic (As) Beryllium (Be) Cadmium (Cd) Chromium (Cr) Cobalt (Co) Lead (Pb) Manganese (Mn) Nickel (Ni) Selenium (Se) 8.0E - 3 lb/GWh 6.0E - 2 lb/GWh 2.0E - 3 lb/GWh 2.0E - 3 lb/GWh 2.0E - 2 lb/GWh 3.0E - 1 lb/GWh 3.0E - 2 lb/GWh 1.0E - 1 lb/GWh 4.1E0 lb/GWh 2.0E - 2 lb/GWh Collect a minimum of 3 dscm per run.

Mercury (Hg) 4.0E - 4 lb/GWh For Method 30B sample volume determination (Section 8.2.4), the*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **82** of **93** estimated Hg concentration should nominally be < 1⁄2 the standard. b. Hydrogen chloride (HCl) 2.0E - 3 lb/MWh For Method 26A, collect a minimum of 1 dscm per run; for Method 26, collect a minimum of 120 liters per run. For ASTM D6348 - 03 2 or Method 320, sample for a minimum of 1 hour. c. Hydrogen fluoride (HF) 5 .0E - 4 lb/MWh For Method 26A, collect a minimum of 3 dscm per run. For ASTM D6348 - 03 2 or Method 320, sample for a minimum of 1 hour. 6. Solid oil derived fuel fired unit. a. Filterable

particulate matter (PM) 3 .0E - 2 lb/MWh 1 Collect a minimum of 1 dscm per run. OR OR Total non - Hg HAP metals 6.0E - 1 lb/GWh Collect a minimum of 1 dscm per run. OR OR Individual HAP Collect a*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **83** of **93** metals: Antimony (Sb) Arsenic (As) Beryllium (Be) Cadmium (Cd) Chromium (Cr) Cobalt (Co) Lead (Pb) Manganese (Mn) Nickel (Ni) Selenium (Se) 8.0E - 3 lb/GWh 3.0E - 3 lb/GWh 6.0E - 4 lb/GWh 7.0E - 4 lb/GWh 6.0E - 3 lb/GWh 2.0E - 3 lb/GWh 2.0E - 2 lb/GWh 7.0E - 3 lb/GWh 4.0E - 2 lb/GWh 6.0E - 3 lb/GWh minimum of 3 dscm per run.

b. Hydrogen chloride (HCl) 4 .0E - 4 lb/MWh For Method 26A, collect a minimum of 3 dscm per run. For ASTM D6348 - 03 2 or Method 320, sample for a minimum of 1 hour. OR Sulfur dioxide (SO 2 ) 3 1 .0 lb/MWh SO 2 CEMS. c. Mercury (Hg) 2.0E - 3 lb/GWh Hg CEMS or Sorbent trap monitoring system only. 1 Gross electric output. 2 Incorporated by reference, see §63.14. 3 You may not use the alternate SO 2 limit if your EGU does not have some form of FGD system (or , in the case of IGCC EGUs, some other acid gas removal system either upstream or downstream of the combined cycle block) and SO 2 CEMS installed. 4 Duct burners on syngas; gross electric output. 5 Duct burners on natural gas; gross electric output . 2 0 . Revise Table 4 to Subpart UUUUU of Part 63 to read as follows: **Table 4 to Subpart UUUUU of Part 63 —**  **Operating Limits for EGUs***** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **84** of **93** As stated in §§63.9991, you must comply with the applicable operating limits: **If you demonstrate compliance using...**  **You must meet these operating limits...**  1. PM CPMS for an existing EGU Maintain the 30 -boiler operating day rolling average PM CPMS output at or below the highest 1 -hour average measured during the most recent performance test demonstrating compliance with the filterable PM, total non -mercury HAP metals (total HAP metals, for liquid oil - fired units), or individual non -mercury HAP metals (individual HAP metals including Hg, for liquid oil - fired units) emissions limitation(s). 2. PM CPMS for a new EGU Maint ain the 30 -boiler operating day rolling average PM CPMS output determined in accordance with the requirements of §63.10023(b)(2) and obtained during the most recent performance test run demonstrating compliance with the filterable PM, total non -mercury HAP metals (total HAP metals, for liquid oil - fired units), or individual non -mercury HAP metals (individual HAP metals including Hg, for liquid oil - fired units) emissions limitation(s).
2 1 . Revise footnote 4 of Table 5 to Subpart UUUUU of Part 63 to read as follows: **Table 5 to Subpart UUUUU of Part 63 —**  **Performance Testing Requirements**  * * * * * 4 When using ASTM D6348

– 03, the following conditions must be met:*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **85** of **93** (1) The test plan preparation and implementation in the Annexes to ASTM D6348

– 03, Sections A1 through A8 are mandatory; (2) For ASTM D6348

– 03 Annex A5 (Analyte Spiking Technique), the percent (%)R must be determined for each target analyte (see Equation A5.5); (3) For the ASTM D6348

– 03 test data to be acceptable for a target analyte, %R must be 70% < R < 130%; and (4) The %R value for each compound must be reported in the test report and all f ield measurements corrected with the calculated %R value for that compound using the following equation: 2 2 . Revise Table 6 to Subpart UUUUU of Part 63 to read as follows: **Table 6 to Subpart UUUUU of Part 63 —**  **Establishing PM CPMS Operating Limits**  As stated in §63.10007, you must comply with the following requirements for establishing operating limits: **If you have an**  **applicable emission**  **limit for...**  **And you choose**

**to establish PM CPMS operating**  **limits, you must...**  **And... Using...**  **According to the fol** **lowing procedures...** 

1. Filterable Particulat e matter (PM), total non mercury HAP metals, individual non mercury HAP metals, total HAP metals, or individual Install,

certify, maintain, and operate a PM CPMS for monitoring emissions discharged to the atmosphere according to §63.10010(h)(1)

. Establish

a site specific operating limit in units of PM CPMS output signal ( e.g. , milliamps , mg/acm, or other raw signal). Data from

the PM CPMS and the PM or HAP metals perfo rmanc e tests. 1. Collect PM

CPMS output data during the entire period of the performance tests. 2. Record the average hourly PM CPMS output for each test run in the three run performance test. 3. Determine the highest 1 -*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **86** of **93** HAP metals for an existing EGU. hour average PM CPMS measured during the performance test demonstrating compliance with the filterable PM or HAP metals emissions limitations. 2. Filterable Particulat e matter (PM), total non mercury HAP metals, individual non mercury HAP metals, total HAP metals, or individual HAP metals for a new EGU. Install,

certify, maintain, and operate a PM CPMS for monitoring emissions discharged to the atmosphere according to §63.10010(h)(1)

. Establish

a site specific operating limit in units of PM CPMS output signal ( e.g. , milliamps , mg/acm, or other raw signal). Data from

the PM CPMS and the PM or HAP metals performanc e tests. 1. Collect PM

CPMS output data during the entire period of the performance tests. 2. Record the average hourly PM CPMS output for each test run in the performance test. 3 . Determine the PM CPMS operating limit in accordance with the requirements of §63.10023(b)(2 ) from data obtained during the performance test demonstrating compliance with the*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **87** of **93** filterable PM or HAP metals emissions limitations.
2 3 . Revise Table 7 to Subpa rt UUUUU of Part 63 to read as follows: **Table 7 to Subpart UUUUU of Part 63 —**  **Demonstrating Continuous Compliance**  As stated in §63.10021, you must show continuous compliance with the emission limitations for affected sources according to the following: **If you use one of the**  **following to meet applicable emissions limits, operating**  **limits, or work practice standards ...**  **You demonstrate continuous compliance by ...** 

1. CEMS to measure filterable PM, SO 2 , HCl, HF, or Hg emissions, or using a sorbent trap monit oring system to measure Hg Calculating the 30 - (or 90 - ) boiler operating day rolling arithmetic average emissions rate in units of the applicable emissions standard basis at the end of each boiler operating day using all of the quality assured hourly average CEMS or sorbent trap data for the previous 30 - (or 90 - ) boiler operating days, excluding data recorded during periods of startup or shutdown. 2. PM CPMS to measure compliance with a parametric operating limit Calculating the 30 - (or 90 - ) boiler operating day rolling arithmetic average of all of the quality assured hourly average PM CPMS output data (e.g., milliamps, PM concentration, raw data signal) collected for all operating hours for the previous 30 - (or 90 - ) boiler operating*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **88** of **93** days, excluding data recorded during periods of startup or shutdown. 3. Site - specific monitoring using CMS for liquid oil - fired EGUs for HCl and HF emission limit monitoring If applicable, by conducting the monitoring in accordance with an approved site - specific monitoring p lan. 4. Quarterly performance testing for coal - fired, solid oil derived fired, or liquid oil - fired EGUs to measure compliance with one or more non - PM (or its alternative emission limits) applicable emissions limit in Table 1 or 2 , or PM (or its alternative emission limits) applicable emissions limit in Table 2 Calculating the results of the testing in units of the applicable emissions standard.

5. Conducting periodic performance tune -ups of your EGU(s) Conducting periodic performance tune -ups of your EGU(s), as specified in §63.10021(e). 6. Work practice standards for coal - fired, liquid oil - fired, or solid oil - derived fuel fired EGUs during startup Operating in accordance with Table 3. 7. Work practice standards for coal - fired, liquid oil - fired, or solid oil - derived fuel fired EGUs during shutdown Operating in accordance with Table 3.

2 4 . Revise Table 9 to Subpart UUUUU of Part 63 to read as follows: **Table 9**  **to Subpart UUUUU of Part 63 —**  **Applicability of General Provisions to Subpart UUUUU**  As stated in §63.100 40 , you must comply with the applicable General Provisions according to the following: **Citation Subject**  **Applies to subpart UUUUU** §63.1 Applicability Yes.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **89** of **93** §63.2 Definitions Yes. Additional terms defined in §63.10042. §63.3 Units and Abbreviations Yes. §63.4 Prohibited Activities and Circumvention Yes. §63.5 Preconstruction Review and Notification Requirements Yes.
§63.6(a), (b)(1) - (b)(5), (b)(7), (c), (f)(2) - (3), (g), (h)(2) - (h)(9), (i), (j) Compliance with Standards and Maintenance Requirements Yes.

§63.6(e)(1)(i) General Duty to minimize emissions No. See §63.10000(b) for general duty requirement. §63.6(e)(1)(ii) Requirement to correct malfunctions ASAP No. §63.6(e)(3) SSM Plan requirements No. §63.6(f)(1) SSM exemption No. §63.6(h)(1) SSM exemption No. §63.7(a), (b), (c), (d), (e)(2) - (e)(9), (f), (g), and (h) Performance Testing Requirements Yes.
§63.7(e)(1) Performance testing No. See §63.10007. §63.8 Monitoring Requirements Yes. 63.8(c)(1)(i) General duty to minimize emissions and CMS operation No. See §63.10000(b) for general duty requirement. §63.8(c)(1)(iii) Requirement to develop SSM Plan for CMS No. §63.8(d)(3) Written procedures for CMS Yes, except for last sentence, which refers to an SSM plan. SSM plans are not required.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **90** of **93** §63.9 Notification requirements Yes, except for the 60 - day notification prior to conducting a performance test in §63.9(d); instead use a 30 - day notification period per §63.10030(d). §63.10(a), (b)(1), (c), (d)(1) - (2), ( e), and (f) Recordkeeping and Reporting Requirements Yes, except for the requirements to submit written reports under §63.10(e)(3)(v). §63.10(b)(2)(i) Recordkeeping of occurrence and duration of startups and shutdowns No.

§63.10(b)(2)(ii) Recordkeeping of malfunctions No. See 63.10001 for recordkeeping of (1) occurrence and duration and (2) actions taken during malfunction. §63.10(b)(2)(iii) Maintenance records Yes. §63.10(b)(2)(iv) Actions taken to minimize emissions during SSM No. §63.10(b)(2)(v) Actions taken to minimize emissions during SSM No. §63.10(b)(2)(vi) Recordkeeping for CMS malfunctions Yes. §63.10(b)(2)(vii)

- (ix) Other CMS requirements Yes. §63.10(b)(3),and (d)(3) - (5) No. §63.10(c)(7) Additional recordkeeping requirements for CMS

– identifying exceedances and excess emissions Yes.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **91** of **93** §63.10(c)(8) Additional recordkeeping requirements for CMS

– identifying exceedances and excess emissions Yes.

§63.10(c)(10) Recording nature and cause of malfunctions No. See 63.10032(g) and (h) for malfunctions recordkeeping requirements. §63.10(c)(11) Recording corrective actions No. See 63.10032(g) and (h) for malfunctions recordkeeping requirements. §63.10(c)(15) Use of SSM Plan No. §63.10(d)(5) SSM reports No. See 63.10021(h) and (i) for malfunction reporting requirements. §63.11 Control Device Requirements No. §63.12 State Authority and Delegation Yes. §63.13 - 63.16 Addresses, Incorporation by Reference, Availability of Information, Performance Track Provisions Yes.

§63.1(a)(5),(a)(7 ) - (a)(9), (b)(2), (c)(3) - (4), (d), 63.6(b)(6), (c)(3), (c)(4), (d), (e)(2), (e)(3)(ii), (h)(3), (h)(5)(iv), 63.8(a)(3), 63.9(b)(3), (h)(4), 63.10(c)(2) - (4), (c)(9). Reserved No.*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **92** of **93** 2 5 . Revise s ection s 4.1 and 5.2.2.2 to Appendix A to Subpart UUUUU of Part 63 to read as follows: Appendix A to Subpart UUUUU

– Hg Monitoring Provisions * * * * * 4.1 Certification Requirements. All Hg CEMS and sorbent trap monitoring systems and the additional monitoring systems used to continuously measure Hg emissions in units of the applicable emissions standard in accordance with this appendix must be certified in a timely manner, such that the initial compliance demonstration is completed no later than the applicable date in §63.9984(f). * * * * * 5.2.2.2 The same RATA performance criteria specified in Table A2 for Hg CEMS also apply to the annual RATAs of the sorbent trap monitoring system. * * * * * 2 6 . Revise s ection 3.1.2.1.3 and correct the heading to section 5.3.4 Conditional Data Validat ion to Appendix B to Subpart UUUUU of Part 63 to read as follows: Appendix B to Subpart UUUUU

– HCl and HF Monitoring Provisions * * * * * 3.1.2.1.3 For the ASTM D6348

– 03 test data to be acceptable for*** E.O. 12866 Review

– Draft

– Do Not Cite, Quote or Release During Review ***

Page **93** of **93** a target analyte, %R must be 70% ≤ R ≤ 130%; and * * * * * 5.3.3 Conditional Data Validation * * * * *