% Efficiencies KVA Phase MVLF STD dEL1 dEL2 dEL3 dEL4 dEL5 dEL6 501ph DL01 99.08%99.16% 99.22%99.25%99.31%99.42% 99.50% 251ph DL02 98.91%99.00% 99.07%99.11%99.18%99.31% 99.41% 5001ph DL03 99.42%99.48% 99.51%99.54%99.57%99.61% 99.69% 1503ph DL04 99.08%99.16% 99.22%99.25%99.31%99.42% 99.50% 15003ph DL05 99.42%99.48% 99.51%99.54%99.57%99.61% 99.69% % Efficiencies BIL groupKVA Phase MVDT STD dEL1 dEL2 dEL3 dEL4 dEL5 dEL6 20-45 3003ph DL09 98.82%98.99% 99.12%99.28%99.38%99.50% 99.59% 20-45 15003ph DL10 99.22%99.31% 99.40%99.50%99.53%99.60% 99.67% 46-95 3003ph DL11 98.67%98.81% 98.94%99.06%99.13%99.32% 99.50% 46-95 15003ph DL12 99.12%99.21% 99.30%99.39%99.46%99.53% 99.59% 96-200 3003ph DL13A 98.63%98.76% 98.85%98.92%99.10%99.29% 99.48% 96-200 20003ph DL13B 99.15%99.23% 99.31%99.38%99.43%99.49% 99.58% % Efficiencies KVA Phase LVDT STD dEL1 dEL2 dEL3 dEL4 dEL5 dEL6 EC3 251ph DL6 98.00%98.23% 98.47%98.60%98.80%98.93% 99.17%

753ph DL7 98.00%98.23% 98.47%98.60%98.80%98.93% 99.17% 3003ph DL8 98.60%98.80% 99.02%99.14%99.25%99.32% 99.44% EC4 EC06 EC08 EC10watts watts

dEL7 STD dEL1 dEL2 dEL3 dEL4 dEL5 dEL6 dEL7 STD

--- 232 212 197 189 174 146 126 --- 230 99.46% 138 126 117 112 103 87 74 68 136 99.73% 1458 1307 1231 1155 1080 979 777 677 1450 99.60% 696 635 590 567 521 438 377 301 690

--- 4375 3920 3693 3466 3239 2936 2332 --- 4350

1660.797avg watts watts dEL7 STD dEL1 dEL2 dEL3 dEL4 dEL5 dEL6 dEL7 STD

--- 1791 1530 1332 1088 936 754 618 --- 1770 99.31% 5896 5211 4527 3769 3542 3012 2483 5211 5850 98.81% 2022 1806 1607 1423 1316 1027 754 1806 1995 99.63% 6659 5972 5287 4603 4072 3542 3088 --- 6600

--- 2084 1883 1745 1638 1362 1073 784 --- 2055

--- 8573 7760 6948 6239 5733 5126 4218 --- 8500

watts watts dEL7 STD dEL1 dEL2 dEL3 dEL4 dEL5 dEL6 dEL7 STD 99.44% 255 225 194 177 152 135 105 70 255 99.44% 765 676 583 532 455 406 314 211 765 99.58% 2130 1822 1485 1301 1134 1027 845 633 2130 NEMA Premium 30 = 30% off current standard% Reduction in watts

dEL1 dEL2 dEL3 dEL4 dEL5 dEL6 dEL7 -8% -15% -18% -24% -37% -45% -7% -14% -17% -24% -36% -45% -50% -10% -15% -20% -26% -32% -46% -53% -8% -15% -18% -24% -37% -45% -56% -10% -15% -20% -26% -32% -46% average % Reduction within BIL group % Reduction in watts watts % Reduction in watts dEL1 dEL2 dEL3 dEL4 dEL5 dEL6 dEL7 STD dEL1 dEL2 dEL3 -14% -25% -39% -47% -57% -65% 1770 -12% -24% -37% -11% -23% -36% -39% -49% -58% -11% 5850 -12% -24% -37% -9% -19% -29% -34% -49% -62% -9% 1995 -9% -20% -29% -10% -20% -30% -38% -46% -53% 6600 -9% -20% -29% -8% -15% -20% -34% -48% -62% 2055 -9% -17% -23% -9% -18% -27% -33% -40% -50% 8500 -9% -17% -23% % Reduction in watts dEL1 dEL2 dEL3 dEL4 dEL5 dEL6 dEL7 -12% -24% -30% -40% -47% -59% -72% -12% -24% -30% -40% -47% -59% -72% -14% -30% -39% -47% -52% -60% -70% NEMA Premium 30 = 30% off current standardPositions as of Dec 2nd Greens NEMA AK+AL Utilities dEL4 dEL1 dEL0.5 EL0 dEL4 dEL0.5 dEL0 EL0 dEL3 dEL1 dEL0.5 EL0 dEL4 dEL1 dEL0.5 EL0 dEL4 dEL1 dEL0.5 EL0 Positions as of Dec 2nd dEL4 dEL5 dEL6 dEL7 Greens NEMA AK+AL Utilities -43% -53% -61% dEL1.5 dEL1.5 dEL1 dEL1 -43% -53% -61% -11% dEL2 dEL2 dEL1 dEL1 -36% -47% -58% -9% dEL2 dEL2 dEL1 dEL1 -36% -47% -58% dEL3 dEL3 dEL1 dEL1 -33% -44% -56% *** *** dEL1 dEL1 -33% -44% -56% *** *** dEL1 dEL1 Positions as of Dec 2nd Greens NEMA AK+AL Utilities

--- EL0 --- --- dEL4 dEL2 --- --- dEL4 dEL2 --- ---2010 Standard Efficiency(linear interpolation of watts) 2010 Standard Watts(linear interpolation of watts) MVDT - 1ph MVDT - 3ph MVDT - 1ph

EC05 EC07 EC09 EC06 EC08 EC10 EC05 45BIL 95BIL >95BIL 45BIL 95BIL >95BIL KVA 45BIL 1598.10% 97.86% --- 1597.50%97.18% --- 15 145 2598.33% 98.12% --- 2597.82%97.54% --- 25 212 3098.41% 98.21% --- 3097.90%97.63% --- 30 242 37.598.49% 98.30% --- 37.598.02%97.77% --- 37.5 287 4598.56% 98.38% --- 4598.10%97.86% --- 45 328 5098.60% 98.42% --- 5098.16%97.92% --- 50 355 7598.73% 98.57% 98.53% 7598.33%98.12% --- 75 482 10098.82% 98.67% 98.63% 10098.45%98.25% --- 100 597 112.598.86% 98.71% 98.68% 112.598.49%98.30% --- 112.5 649 15098.94% 98.80% 98.77% 15098.60%98.42% --- 150 806 16798.96% 98.83% 98.80% 16798.64%98.47% --- 167 878 22599.05% 98.92% 98.89% 22598.73%98.57% 98.53% 225 1084 25099.07% 98.95% 98.91% 25098.77%98.61% 98.57% 250 1173 30099.12% 99.00% 98.96% 30098.82%98.67% 98.63% 300 1337 33399.14% 99.03% 98.99% 33398.85%98.71% 98.67% 333 1444 50099.22% 99.12% 99.09% 50098.96%98.83% 98.80% 500 1965 66799.27% 99.18% 99.15% 66799.04%98.92% 98.88% 667 2452 75099.29% 99.21% 99.18% 75099.07%98.95% 98.91% 750 2673 83399.31% 99.23% 99.20% 83399.10%98.98% 98.94% 833 2894 100099.14%99.03% 98.99% 150099.22%99.12% 99.09% 200099.27%99.18% 99.15% 250099.31%99.23% 99.20% 2010 Standard: 1ph as 1/3 of 3ph-3xKVA 100DL09/3 500DL10/3 667

**bold = driver** Consensus #1(linear interpolation of watts) Consensus #1(linear interpolation of watts) MVDT - 1ph MVDT - 3ph MVDT - 1ph

EC05 EC07 EC09 EC06 EC08 EC10 EC05 45BIL 95BIL >95BIL 45BIL 95BIL >95BIL 45BIL 1598.10% 97.86% --- 1597.74%97.55% --- 15 145 2598.33% 98.12% --- 2598.02%97.85% --- 25 212 3098.41% 98.21% --- 3098.09%97.93% --- 30 242 37.598.49% 98.30% --- 37.598.20%98.05% --- 37.5 287 4598.56% 98.38% --- 4598.27%98.12% --- 45 328 5098.60% 98.42% --- 5098.32%98.18% --- 50 355 7598.73% 98.57% 98.53% 7598.48%98.34% --- 75 482 10098.82% 98.67% 98.63% 10098.58%98.46% --- 100 597 112.598.86% 98.71% 98.68% 112.598.62%98.50% --- 112.5 649 15098.94% 98.80% 98.77% 15098.71%98.60% --- 150 806 16798.96% 98.83% 98.80% 16798.75%98.65% --- 167 878 22599.05% 98.92% 98.89% 22598.84%98.74% 98.61% 225 1084 25099.07% 98.95% 98.91% 25098.87%98.77% 98.65% 250 1173 30099.12% 99.00% 98.96% 30098.92% **98.81%**98.71% 300 1337 33399.14% 99.03% 98.99% 33398.95%98.86% 98.75% 333 1444 50099.22% 99.12% 99.09% 50099.05%98.96% 98.86% 500 1965 66799.27% 99.18% 99.15% 66799.14%99.12% 99.03% 667 2452 75099.29% 99.21% 99.18% 75099.17%99.17% 99.09% 750 267383399.31% 99.23% 99.20% 83399.20%99.19% 99.11% 833 2894 100099.24%99.23% 99.15% DL09 dEL0.5 1500**99.31% 99.30%** 99.23% DL10 dEL1.0 200099.36%99.35% 99.28% DL11 dEL1.0 250099.39%99.38% 99.32% **DL12 dEL2.0**  DL13 min(2010, EC08 watts + 10%) dEL0.5 dEL1 EC08 + EC06 * EC05 min(2010, EC06 watts * 1.3) + 3/4 rule+ 3/4 rule 10% 1.3 EC07 min(2010, EC08 watts * 1.3) dEL1 dEL2 EC06 * EC09 min(2010, EC10 watts * 1.3) + 3/4 rule+ 3/4 rule 1.3(linear interpolation of watts) 2010 Standard Watts(linear interpolation of watts) 2010 Standard Wattsrelative to 95BIL(linear interpolation of watts) MVDT - 3ph MVDT - 1ph EC07 EC09 EC06 EC08 EC10 EC05 EC07 EC09 95BIL >95BIL KVA 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL KVA 164 --- 15 192 218 --- 15 0.9 1.0 --- 15 240 --- 25 279 315 --- 25 0.9 1.0 --- 25 273 --- 30 322 364 --- 30 0.9 1.0 --- 30 324 --- 37.5 379 428 --- 37.5 0.9 1.0 --- 37.5 371 --- 45 436 492 --- 45 0.9 1.0 --- 45 401 --- 50 469 530 --- 50 0.9 1.0 --- 50 544 559 75 637 719 --- 75 0.9 1.0 1.03 75 674 695 100 787 888 --- 100 0.9 1.0 1.03 100 733 754 112.5 862 973 --- 112.5 0.9 1.0 1.03 112.5 909 933 150 1065 1204 --- 150 0.9 1.0 1.03 150 989 1014 167 1152 1301 --- 167 0.9 1.0 1.03 167 1225 1268 225 1447 1632 1678 225 0.9 1.0 1.04 225 1326 1378 250 1562 1762 1813 250 0.9 1.0 1.04 250 1510 1571 300 1791 2022 2084 300 0.9 1.0 1.04 300 1631 1699 333 1929 2177 2241 333 0.9 1.0 1.04 333 2220 2296 500 2627 2960 3036 500 0.9 1.0 1.03 500 2757 2859 667 3224 3641 3769 667 0.9 1.0 1.04 667 2995 3109 750 3520 3979 4133 750 0.9 1.0 1.04 750 3232 3359 833 3792 4284 4454 833 0.9 1.0 1.04 833 1000 4337 4898 5102 1000 1500 5896 6659 6888 1500 2000 7354 8268 8573 2000 2500 8685 9700 10081 2500 2010 Standard: 1ph as 1/3 of 3ph-3xKVA DL11/3DL13A/3 300DL09 DL11 DL13A DL12/3 1500DL10 DL12

DL13B/3 2000 DL13B

(linear interpolation of watts) Consensus #1 Wattsrelative to 95BIL(linear interpolation of watts) MVDT - 3ph MVDT - 1ph EC07 EC09 EC06 EC08 EC10 EC05 EC07 EC09 95BIL >95BIL 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL KVA 164 --- 15 174 189 --- 15 0.9 1.0 --- 15 240 --- 25 253 275 --- 25 0.9 1.0 --- 25 273 --- 30 292 317 --- 30 0.9 1.0 --- 30 324 --- 37.5 344 374 --- 37.5 0.9 1.0 --- 37.5 371 --- 45 396 430 --- 45 0.9 1.0 --- 45 401 --- 50 427 464 --- 50 0.9 1.0 --- 50 544 559 75 581 631 --- 75 0.9 1.0 1.03 75 674 695 100 718 781 --- 100 0.9 1.0 1.03 100 733 754 112.5 787 855 --- 112.5 0.9 1.0 1.03 112.5 909 933 150 977 1061 --- 150 0.9 1.0 1.03 150 989 1014 167 1055 1147 --- 167 0.9 1.0 1.03 167 1225 1268 225 1324 1439 1582 225 0.9 1.0 1.04 225 1326 1378 250 1430 1554 1709 250 0.9 1.0 1.04 250 1510 1571 300 **1643** 1785 1964 300 0.9 1.0 1.04 300 1631 1699 333 1769 1922 2115 333 0.9 1.0 1.04 333 2220 2296 500 2409 2618 2880 500 0.9 1.0 1.03 500 2757 2859 667 2900 2969 3266 667 0.9 1.0 1.04 667 2995 3109 750 3144 3144 3458 750 0.9 1.0 1.04 7503232 3359 833 3376 3395 3735 833 0.9 1.0 1.04 833 1000 3845 3901 4291 1000 1500 5211 5287 5816 1500 2000 6466 6560 7216 2000 2500 7644 7755 8531 2500 EC08 * EC10 dEL0.5 dEL1 EC08 + 1.3 + 3/4 rule+ 3/4 rule 10% EC08 * EC10 * dEL1 dEL2 1.3 1.3 + 3/4 rule+ 3/4 rule(linear interpolation of watts) 2010 Standard 1ph/3ph watts(linear interpolation of watts) 2010 Standard watts correctly extrapolated MVDT - 3ph MVDT - 1ph MVDT - 3ph EC06 EC08 EC10 EC05 EC07 EC09 EC06 EC08 EC10 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL 0.9 1.0 --- 15 0.76 0.75 --- 15 279 552 --- 0.9 1.0 --- 25 0.76 0.76 --- 25 363 633 --- 0.9 1.0 --- 30 0.75 0.75 --- 30 401 671 --- 0.9 1.0 --- 37.5 0.76 0.76 --- 37.5 456 724 --- 0.9 1.0 --- 45 0.75 0.75 --- 45 508 775 --- 0.9 1.0 --- 50 0.76 0.76 --- 50 541 807 --- 0.9 1.0 --- 75 0.76 0.76 --- 75 698 959 --- 0.9 1.0 --- 100 0.76 0.76 --- 100 842 1099 --- 0.9 1.0 --- 112.5 0.75 0.75 --- 112.5 911 1166 --- 0.9 1.0 --- 150 0.76 0.75 --- 150 1106 1356 --- 0.9 1.0 --- 167 0.76 0.76 --- 167 1190 1438 --- 0.9 1.0 1.03 225 0.75 0.75 0.76 225 1463 1703 1768 0.9 1.0 1.03 250 0.75 0.75 0.76 250 1575 1812 1876 0.9 1.0 1.03 300 0.75 0.75 0.75 300 1791 2022 2084 0.9 1.0 1.03 333 0.75 0.75 0.76 333 1929 2156 2216 0.9 1.0 1.03 500 0.75 0.75 0.76 500 2580 2789 2842 0.9 1.0 1.04 667 0.76 0.76 0.76 667 3179 3371 3417 0.9 1.0 1.04 750 0.76 0.75 0.75 750 3640 4345 4878 0.9 1.0 1.04 833 0.76 0.75 0.75 833 3911 4623 5156 0.9 1.0 1.04 1000 4437 5162 5697 0.9 1.0 1.03 1500 5896 6659 7196 0.9 1.0 1.04 2000 7236 8033 8573 0.9 1.0 1.04 2500 8494 9323 9865 NL/TL 0.50 0.50 0.50 nominal BIL 30 95 125 air strike 3.79 12.00 15.79 1500KVA base coil 30.00 30.00 30.00 1500KVA base window 33.79 42.00 45.79 1500 KVA rel to 95BIL 0.80 1.00 1.09 300KVA base coil 20.06 20.06 20.06 300KVA base window 23.85 32.06 35.85 300KVA rel to 95BIL 0.74 1.00 1.12 (linear interpolation of watts) Consensus #1 1ph/3ph(linear interpolation of watts) Consensus #1 % Reduction in watts(linear interpolation of watts) MVDT - 3ph MVDT - 1ph MVDT - 1ph EC06 EC08 EC10 EC05 EC07 EC09 EC05 EC07 EC09 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL 0.9 1.0 --- 15 0.84 0.87 --- 15 0% 0% --- 0.9 1.0 --- 25 0.84 0.87 --- 25 0% 0% --- 0.9 1.0 --- 30 0.83 0.86 --- 30 0% 0% --- 0.9 1.0 --- 37.5 0.84 0.87 --- 37.5 0% 0% --- 0.9 1.0 --- 45 0.83 0.86 --- 45 0% 0% --- 0.9 1.0 --- 50 0.83 0.87 --- 50 0% 0% --- 0.9 1.0 --- 75 0.83 0.86 --- 75 0% 0% 0% 0.9 1.0 --- 100 0.83 0.86 --- 100 0% 0% 0% 0.9 1.0 --- 112.5 0.83 0.86 --- 112.5 0% 0% 0% 0.9 1.0 --- 150 0.83 0.86 --- 150 0% 0% 0% 0.9 1.0 --- 167 0.83 0.86 --- 167 0% 0% 0% 0.9 1.0 1.10 225 0.82 0.85 0.80 225 0% 0% 0% 0.9 1.0 1.10 250 0.82 0.85 0.81 250 0% 0% 0% 0.9 1.0 1.10 300 0.81 0.85 0.80 300 0% 0% 0% 0.9 1.0 1.10 333 0.82 0.85 0.80 333 0% 0% 0% 0.9 1.0 1.10 500 0.82 0.85 0.80 500 0% 0% 0% 1.0 1.0 1.10 667 0.85 0.93 0.88 667 0% 0% 0% 1.0 1.0 1.10 750 0.85 0.95 0.90 750 0% 0% 0%1.0 1.0 1.10 833 0.86 0.95 0.90 833 0% 0% 0% 1.0 1.0 1.10 1.0 1.0 1.10 1.0 1.0 1.10 1.0 1.0 1.102010 Standard understatement of losses MVDT - 3ph EC06 EC08 EC10 KVA 45BIL 95BIL >95BIL 15 45% 154% --- 25 30% 101% --- 30 25% 84% --- 37.5 20% 69% --- 45 17% 57% --- 50 15% 52% --- 75 10% 34% --- 100 7% 24% --- 112.5 6% 20% --- 150 4% 13% --- 167 3% 10% --- 225 1% 4% 5% 250 1% 3% 3% 300 0% 0% 0% 333 0% -1% -1% 500 -2% -6% -6% 667 -1% -7% -9% 750 3% 9% 18% 833 3% 8% 16% 1000 2% 5% 12% 1500 0% 0% 4% 2000 -2% -3% 0% 2500 -2% -4% -2%

(linear interpolation of watts) Consensus #1 watts correctly extrapolated Consensus #1 understatement of losses MVDT - 3ph MVDT - 3ph MVDT - 3ph EC06 EC08 EC10 EC06 EC08 EC10 EC06 KVA 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL KVA 45BIL 15 -10% -13% --- 15 256 487 --- 15 47% 25 -9% -13% --- 25 333 559 --- 25 32% 30 -9% -13% --- 30 368 592 --- 30 26% 37.5 -9% -13% --- 37.5 418 639 --- 37.5 22% 45 -9% -13% --- 45 466 684 --- 45 18% 50 -9% -12% --- 50 497 713 --- 50 16% 75 -9% -12% --- 75 640 847 --- 75 10% 100 -9% -12% --- 100 772 971 --- 100 8% 112.5 -9% -12% --- 112.5 835 1029 --- 112.5 6% 150 -8% -12% --- 150 1014 1197 --- 150 4% 167 -8% -12% --- 167 1091 1269 --- 167 3% 225 -9% -12% -6% 225 1342 1503 1666 225 1% 250 -8% -12% -6% 250 1444 1600 1768 250 1% 300 -8% -12% -6% 300 1643 1785 1964 300 0% 333 -8% -12% -6% 333 1769 1903 2088 333 0% 500 -8% -12% -5% 500 2366 2462 2678 500 -2% 667 -10% -18% -13% 667 2915 2976 3220 667 1% 750 -11% -21% -16% 750 3217 3450 4106 750 2%833 -11% -21% -16% 833 3456 3671 4340 833 2%

1000 -11% -20% -16% 1000 3921 4099 4795 1000 2% 1500 -12% -21% -16% 1500 5211 5287 6057 1500 0% 2000 -12% -21% -16% 2000 6395 6378 7216 2000 -1% 2500 -12% -20% -15% 2500 7507 7403 8304 2500 -2% NL/TL 0.50 0.50 0.50 nominal BIL 30 95 125 air strike 3.79 12.00 15.79 1500KVA base coil 30.00 30.00 30.00 1500KVA base window 33.79 42.00 45.79 1500 KVA rel to 95BIL 0.80 1.00 1.09 300KVA base coil 20.06 20.06 20.06 300KVA base window 23.85 32.06 35.85 300KVA rel to 95BIL 0.74 1.00 1.12Consensus #1 understatement of losses MVDT - 3ph

EC08 EC10 95BIL >95BIL 158% --- 104% --- 87% --- 71% --- 59% --- 54% --- 34% --- 24% --- 20% --- 13% --- 11% --- 5% 5% 3% 3% 0% 0% -1% -1% -6% -7% 0% -1% 10% 19%8% 16% 5% 12% 0% 4% -3% 0% -5% -3%2010 Standard Efficiency(linear interpolation of watts) 2010 Standard Watts(linear interpolation of watts) MVDT - 1ph MVDT - 3ph MVDT - 1ph

EC05 EC07 EC09 EC06 EC08 EC10 EC05 45BIL 95BIL >95BIL 45BIL 95BIL >95BIL KVA 45BIL 1598.10% 97.86% --- 1597.50%97.18% --- 15 145 2598.33% 98.12% --- 2597.82%97.54% --- 25 212 3098.41% 98.21% --- 3097.90%97.63% --- 30 242 37.598.49% 98.30% --- 37.598.02%97.77% --- 37.5 287 4598.56% 98.38% --- 4598.10%97.86% --- 45 328 5098.60% 98.42% --- 5098.16%97.92% --- 50 355 7598.73% 98.57% 98.53% 7598.33%98.12% --- 75 482 10098.82% 98.67% 98.63% 10098.45%98.25% --- 100 597 112.598.86% 98.71% 98.68% 112.598.49%98.30% --- 112.5 649 15098.94% 98.80% 98.77% 15098.60%98.42% --- 150 806 16798.96% 98.83% 98.80% 16798.64%98.47% --- 167 878 22599.05% 98.92% 98.89% 22598.73%98.57% 98.53% 225 1084 25099.07% 98.95% 98.91% 25098.77%98.61% 98.57% 250 1173 30099.12% 99.00% 98.96% 30098.82%98.67% 98.63% 300 1337 33399.14% 99.03% 98.99% 33398.85%98.71% 98.67% 333 1444 50099.22% 99.12% 99.09% 50098.96%98.83% 98.80% 500 1965 66799.27% 99.18% 99.15% 66799.04%98.92% 98.88% 667 2452 75099.29% 99.21% 99.18% 75099.07%98.95% 98.91% 750 2673 83399.31% 99.23% 99.20% 83399.10%98.98% 98.94% 833 2894 100099.14%99.03% 98.99% 150099.22%99.12% 99.09% 200099.27%99.18% 99.15% 250099.31%99.23% 99.20% 2010 Standard: 1ph as 1/3 of 3ph-3xKVA 100DL09/3 500DL10/3 667

**bold = driver** DOE d111221(linear interpolation of watts) DOE d111221(linear interpolation of watts) MVDT - 1ph MVDT - 3ph MVDT - 1ph

EC05 EC07 EC09 EC06 EC08 EC10 EC05 45BIL 95BIL >95BIL 45BIL 95BIL >95BIL 45BIL 15**98.10% 97.86%**  --- 15**97.50% 97.18%**  --- 15 145 25**98.33% 98.12%**  --- 2597.82%97.54% --- 25 212 3098.41% 98.21% --- 30**97.90% 97.63%**  --- 30 242 37.5**98.49% 98.30%**  --- 37.598.02%97.77% --- 37.5 287 4598.56% 98.38% --- 45**98.10% 97.86%**  --- 45 328 50**98.60% 98.42%**  --- 5098.16%97.93% --- 50 355 75**98.73% 98.57%** **98.53%** 75**98.33% 98.13%**  --- 75 482 100**98.82% 98.67%** **98.63%** 10098.47%98.29% --- 100 597 112.598.86% 98.71% 98.68% 112.5**98.52% 98.35%**  --- 112.5 649 15098.94% 98.80% 98.77% 150**98.65% 98.51%**  --- 150 806 167**98.96% 98.83%** **98.80%** 16798.70%98.56% --- 167 878 22599.05% 98.92% 98.89% 225**98.82% 98.69%** **98.57%** 225 1084 250**99.07% 98.95%** **98.91%** 25098.86%98.74% 98.62% 250 1173 30099.12% 99.00% 98.96% 300**98.93% 98.81%** **98.69%** 300 1337 333**99.14% 99.03%** **98.99%** 33398.97%98.85% 98.74% 333 1444 500**99.22% 99.12%** **99.09%** 500**99.09% 98.99%** **98.89%** 500 1965 667**99.27% 99.18%** **99.15%** 66799.18%99.09% 98.99% 667 2452 75099.29% 99.21% 99.18% 750**99.21% 99.12%** **99.02%** 750 2673833**99.31% 99.23%** **99.20%** 83399.24%99.15% 99.06% 833 2894 1000**99.28% 99.20%** **99.11% DOE Draft 111221**  1500**99.37% 99.30%** **99.21%** 2000**99.43% 99.36%** **99.28%** 2500**99.47% 99.41%** **99.33%**(linear interpolation of watts) 2010 Standard Watts(linear interpolation of watts) 2010 Standard Wattsrelative to 95BIL(linear interpolation of watts) MVDT - 3ph MVDT - 1ph EC07 EC09 EC06 EC08 EC10 EC05 EC07 EC09 95BIL >95BIL KVA 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL KVA 164 --- 15 192 218 --- 15 0.9 1.0 --- 15 240 --- 25 279 315 --- 25 0.9 1.0 --- 25 273 --- 30 322 364 --- 30 0.9 1.0 --- 30 324 --- 37.5 379 428 --- 37.5 0.9 1.0 --- 37.5 371 --- 45 436 492 --- 45 0.9 1.0 --- 45 401 --- 50 469 530 --- 50 0.9 1.0 --- 50 544 559 75 637 719 --- 75 0.9 1.0 1.03 75 674 695 100 787 888 --- 100 0.9 1.0 1.03 100 733 754 112.5 862 973 --- 112.5 0.9 1.0 1.03 112.5 909 933 150 1065 1204 --- 150 0.9 1.0 1.03 150 989 1014 167 1152 1301 --- 167 0.9 1.0 1.03 167 1225 1268 225 1447 1632 1678 225 0.9 1.0 1.04 225 1326 1378 250 1562 1762 1813 250 0.9 1.0 1.04 250 1510 1571 300 1791 2022 2084 300 0.9 1.0 1.04 300 1631 1699 333 1929 2177 2241 333 0.9 1.0 1.04 333 2220 2296 500 2627 2960 3036 500 0.9 1.0 1.03 500 2757 2859 667 3224 3641 3769 667 0.9 1.0 1.04 667 2995 3109 750 3520 3979 4133 750 0.9 1.0 1.04 750 3232 3359 833 3792 4284 4454 833 0.9 1.0 1.04 833 1000 4337 4898 5102 1000 1500 5896 6659 6888 1500 2000 7354 8268 8573 2000 2500 8685 9700 10081 2500 2010 Standard: 1ph as 1/3 of 3ph-3xKVA DL11/3DL13A/3 300DL09 DL11 DL13A DL12/3 1500DL10 DL12

DL13B/3 2000 DL13B

(linear interpolation of watts) DOE d1112211 Wattsrelative to 95BIL(linear interpolation of watts) MVDT - 3ph MVDT - 1ph EC07 EC09 EC06 EC08 EC10 EC05 EC07 EC09 95BIL >95BIL 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL KVA 164 --- 15 192 218 --- 15 0.9 1.0 --- 15 240 --- 25 279 315 --- 25 0.9 1.0 --- 25 273 --- 30 322 364 --- 30 0.9 1.0 --- 30 324 --- 37.5 379 428 --- 37.5 0.9 1.0 --- 37.5 371 --- 45 436 492 --- 45 0.9 1.0 --- 45 401 --- 50 469 529 --- 50 0.9 1.0 --- 50 544 559 75 637 715 --- 75 0.9 1.0 1.03 75 674 695 100 776 867 --- 100 0.9 1.0 1.03 100 733 754 112.5 845 944 --- 112.5 0.9 1.0 1.03 112.5 909 933 150 1026 1134 --- 150 0.9 1.0 1.03 150 989 1014 167 1098 1216 --- 167 0.9 1.0 1.03 167 1225 1268 225 1343 1493 1632 225 0.9 1.0 1.04 225 1326 1378 250 1436 1598 1752 250 0.9 1.0 1.04 250 1510 1571 300 1622 1806 1991 300 0.9 1.0 1.04 300 1631 1699 333 1733 1929 2126 333 0.9 1.0 1.04 333 2220 2296 500 2296 2551 2806 500 0.9 1.0 1.03 500 2757 2859 667 2757 3071 3411 667 0.9 1.0 1.04 667 2995 3109 750 2986 3329 3711 750 0.9 1.0 1.04 7503232 3359 833 3199 3563 3970 833 0.9 1.0 1.04 833 1000 3626 4032 4490 1000 1500 4755 5287 5972 1500 2000 5733 6441 7252 2000 2500 6660 7419 8431 2500(linear interpolation of watts) 2010 Standard 1ph/3ph watts(linear interpolation of watts) 2010 Standard watts correctly extrapolated MVDT - 3ph MVDT - 1ph MVDT - 3ph EC06 EC08 EC10 EC05 EC07 EC09 EC06 EC08 EC10 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL 0.9 1.0 --- 15 0.76 0.75 --- 15 279 552 --- 0.9 1.0 --- 25 0.76 0.76 --- 25 363 633 --- 0.9 1.0 --- 30 0.75 0.75 --- 30 401 671 --- 0.9 1.0 --- 37.5 0.76 0.76 --- 37.5 456 724 --- 0.9 1.0 --- 45 0.75 0.75 --- 45 508 775 --- 0.9 1.0 --- 50 0.76 0.76 --- 50 541 807 --- 0.9 1.0 --- 75 0.76 0.76 --- 75 698 959 --- 0.9 1.0 --- 100 0.76 0.76 --- 100 842 1099 --- 0.9 1.0 --- 112.5 0.75 0.75 --- 112.5 911 1166 --- 0.9 1.0 --- 150 0.76 0.75 --- 150 1106 1356 --- 0.9 1.0 --- 167 0.76 0.76 --- 167 1190 1438 --- 0.9 1.0 1.03 225 0.75 0.75 0.76 225 1463 1703 1768 0.9 1.0 1.03 250 0.75 0.75 0.76 250 1575 1812 1876 0.9 1.0 1.03 300 0.75 0.75 0.75 300 1791 2022 2084 0.9 1.0 1.03 333 0.75 0.75 0.76 333 1929 2156 2216 0.9 1.0 1.03 500 0.75 0.75 0.76 500 2580 2789 2842 0.9 1.0 1.04 667 0.76 0.76 0.76 667 3179 3371 3417 0.9 1.0 1.04 750 0.76 0.75 0.75 750 3640 4345 4878 0.9 1.0 1.04 833 0.76 0.75 0.75 833 3911 4623 5156 0.9 1.0 1.04 1000 4437 5162 5697 0.9 1.0 1.03 1500 5896 6659 7196 0.9 1.0 1.04 2000 7236 8033 8573 0.9 1.0 1.04 2500 8494 9323 9865 NL/TL 0.50 0.50 0.50 nominal BIL 30 95 125 air strike 3.79 12.00 15.79 1500KVA base coil 30.00 30.00 30.00 1500KVA base window 33.79 42.00 45.79 1500 KVA rel to 95BIL 0.80 1.00 1.09 300KVA base coil 20.06 20.06 20.06 300KVA base window 23.85 32.06 35.85 300KVA rel to 95BIL 0.74 1.00 1.12 (linear interpolation of watts) DOE d111221 1ph/3ph(linear interpolation of watts) DOE d111221 % Reduction in watts(linear interpolation of watts) MVDT - 3ph MVDT - 1ph MVDT - 1ph EC06 EC08 EC10 EC05 EC07 EC09 EC05 EC07 EC09 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL 0.9 1.0 --- 15 0.76 0.75 --- 15 0% 0% --- 0.9 1.0 --- 25 0.76 0.76 --- 25 0% 0% --- 0.9 1.0 --- 30 0.75 0.75 --- 30 0% 0% --- 0.9 1.0 --- 37.5 0.76 0.76 --- 37.5 0% 0% --- 0.9 1.0 --- 45 0.75 0.75 --- 45 0% 0% --- 0.9 1.0 --- 50 0.76 0.76 --- 50 0% 0% --- 0.9 1.0 --- 75 0.76 0.76 --- 75 0% 0% 0% 0.9 1.0 --- 100 0.77 0.78 --- 100 0% 0% 0% 0.9 1.0 --- 112.5 0.77 0.78 --- 112.5 0% 0% 0% 0.9 1.0 --- 150 0.79 0.80 --- 150 0% 0% 0% 0.9 1.0 --- 167 0.80 0.81 --- 167 0% 0% 0% 0.9 1.0 1.09 225 0.81 0.82 0.78 225 0% 0% 0% 0.9 1.0 1.10 250 0.82 0.83 0.79 250 0% 0% 0% 0.9 1.0 1.10 300 0.82 0.84 0.79 300 0% 0% 0% 0.9 1.0 1.10 333 0.83 0.85 0.80 333 0% 0% 0% 0.9 1.0 1.10 500 0.86 0.87 0.82 500 0% 0% 0% 0.9 1.0 1.11 667 0.89 0.90 0.84 667 0% 0% 0% 0.9 1.0 1.11 750 0.90 0.90 0.84 750 0% 0% 0%0.9 1.0 1.11 833 0.90 0.91 0.85 833 0% 0% 0% 0.9 1.0 1.11 0.9 1.0 1.13 0.9 1.0 1.13 0.9 1.0 1.142010 Standard understatement of losses MVDT - 3ph EC06 EC08 EC10 KVA 45BIL 95BIL >95BIL 15 45% 154% --- 25 30% 101% --- 30 25% 84% --- 37.5 20% 69% --- 45 17% 57% --- 50 15% 52% --- 75 10% 34% --- 100 7% 24% --- 112.5 6% 20% --- 150 4% 13% --- 167 3% 10% --- 225 1% 4% 5% 250 1% 3% 3% 300 0% 0% 0% 333 0% -1% -1% 500 -2% -6% -6% 667 -1% -7% -9% 750 3% 9% 18% 833 3% 8% 16% 1000 2% 5% 12% 1500 0% 0% 4% 2000 -2% -3% 0% 2500 -2% -4% -2%

(linear interpolation of watts) DOE d111221 watts correctly extrapolated DOE d111221 understatement of losses MVDT - 3ph MVDT - 3ph MVDT - 3ph EC06 EC08 EC10 EC06 EC08 EC10 EC06 KVA 45BIL 95BIL >95BIL KVA 45BIL 95BIL >95BIL KVA 45BIL 15 0% 0% --- 15 253 493 --- 15 32% 25 0% 0% --- 25 328 566 --- 25 18% 30 0% 0% --- 30 363 599 --- 30 13% 37.5 0% 0% --- 37.5 413 647 --- 37.5 9% 45 0% 0% --- 45 460 692 --- 45 6% 50 0% 0% --- 50 490 721 --- 50 5% 75 0% -1% --- 75 632 857 --- 75 -1% 100 -1% -2% --- 100 763 982 --- 100 -2% 112.5 -2% -3% --- 112.5 825 1042 --- 112.5 -2% 150 -4% -6% --- 150 1002 1211 --- 150 -2% 167 -5% -7% --- 167 1078 1284 --- 167 -2% 225 -7% -9% -3% 225 1325 1522 1690 225 -1% 250 -8% -9% -3% 250 1427 1619 1793 250 -1% 300 -9% -11% -4% 300 1622 1806 1991 300 0% 333 -10% -11% -5% 333 1747 1926 2117 333 1% 500 -13% -14% -8% 500 2337 2492 2716 500 2% 667 -14% -16% -9% 667 2879 3012 3265 667 4% 750 -15% -16% -10% 750 2935 3450 4127 750 -2%833 -16% -17% -11% 833 3154 3671 4362 833 -1%

1000 -16% -18% -12% 1000 3578 4099 4819 1000 -1% 1500 -19% -21% -13% 1500 4755 5287 6087 1500 0% 2000 -22% -22% -15% 2000 5836 6378 7252 2000 2% 2500 -23% -24% -16% 2500 6850 7403 8346 2500 3% NL/TL 0.50 0.50 0.50 nominal BIL 30 95 125 air strike 3.79 12.00 15.79 1500KVA base coil 30.00 30.00 30.00 1500KVA base window 33.79 42.00 45.79 1500 KVA rel to 95BIL 0.80 1.00 1.09 300KVA base coil 20.06 20.06 20.06 300KVA base window 23.85 32.06 35.85 300KVA rel to 95BIL 0.74 1.00 1.12DOE d111221 understatement of losses MVDT - 3ph

EC08 EC10 95BIL >95BIL 127% --- 79% --- 65% --- 51% --- 41% --- 36% --- 20% --- 13% --- 10% --- 7% --- 6% --- 2% 4% 1% 2% 0% 0% 0% 0% -2% -3% -2% -4% 4% 11%3% 10% 2% 7% 0% 2% -1% 0% 0% -1%