Skip to Main Page ContentSkip to SearchSkip to Site Map NavigationSkip to Footer Links

        - Home

        - FAQ
        - Glossary
        - Facility Locator
        - What's New
        - Site Help
        - Index A-Z
        - Contact Us
        - Browse Aloud
        - Email Updates

Report a Safety Concern

      - Nuclear Reactors  - Power Reactors
- Research & Test Reactors
- Operating Reactors
- Operator Licensing
- New Reactors
- Advanced Reactors
- Operator Licensing for New Reactors
- Nuclear Reactor Quick Links
 
      - Nuclear Materials  - Special Nuclear Material
- Source Material
- Byproduct Material
- Med, Ind, & Academic Uses
- Source Materials Facilities
- Uranium Recovery
- Fuel Cycle Facilities
- Materials Transportation
- Nuclear Materials Quick Links
 
      - Radioactive Waste  - Low-Level Waste
- Waste Incidental to Reprocessing
- High-Level Waste
- Uranium Mill Tailings
- Low-Level Waste Disposal
- High-Level Waste Disposal
- Storage of Spent Nuclear Fuel
- Transporation of Spent Nuclear Fuel
- Radioactive Waste Quick Links
 
      - Nuclear Security  - Domestic Safeguards
- Information Security
- Radioactive Material Security
- Contact Us
 
      - Public Meetings & Involvement  - The NRC Approach to Open Government
- About Meetings Open to the Public
- Conferences & Symposia
- Documents for Comment
- Facilitating Stakeholder Involvement
- NRC Information Quality Guidelines
- Subscribe to E-mail Updates
- Commission Schedule
- Public Meeting Schedule
 
      - NRC Library  - Basic References
- Document Collections
- ADAMS Public Documents
- Public Document Room
- Get Copies of Documents
- FOIA & Privacy Act Requests
- Photos & Video
- Records Management 
- Withholding of Sensitive Information
- FAQ Index
- HLW Licensing Network
- Adjudications (Hearings)
 
      - About NRC  - The Commission
- Governing Legislation
- Plans, Budget, & Performance
- Organization & Functions
- Locations
- History
- Values
- Direction-Setting & Policymaking
- Radiation Protection
- Fire Protection
- How We Regulate
- Emergency Preparedness & Response
- Public Affairs
- Congressional Affairs
- International Programs
- State & Tribal Programs
- Alternative Dispute Resolution Programs
- Employment Opportunities
- Contracting Opportunities
- Grant Opportunities
- Civil Rights
 

PrintShare

Email

Print

TwitterFacebookMySpace

DelicousStumbleDigg

More...

HomeNRC LibraryDocument CollectionsGeneral CommunicationsInformation Notices1994

# 

```

UNITED STATES
NUCLEAR REGULATORY COMMISSION
OFFICE OF NUCLEAR REACTOR REGULATION
WASHINGTON, D.C. 20555

April 14, 1994


NRC INFORMATION NOTICE 94-31:  POTENTIAL FAILURE OF WILCO, LEXAN-TYPE HN-4-L
 FIRE HOSE NOZZLES


Addressees

All holders of operating licenses or construction permits for nuclear power
reactors.

Purpose

The U.S. Nuclear Regulatory Commission (NRC) is issuing this information
notice to alert the addressees of the potential for failure of Lexan-
type HN-4-L fire hose nozzles.  It is expected that recipients will review the
information for applicability to their facilities and consider actions, as
appropriate, to avoid similar problems.  However, suggestions contained in
this information notice are not NRC requirements; therefore, no specific
action or written response is required.

Description of Circumstances

On August 3, 1992, the licensee for the H.B. Robinson facility experienced a
failure of a 1 1/2-inch Lexan-type HN-4-L fire hose nozzle during a routine
fire hose hydrostatic pressure test.  Following the failure, the licensee
revised their procedures to require the use of a ball-style shutoff nozzle
during future pressurization tests.  On June 17, 1993, the licensee
experienced another failure of a Lexan-type HN-4-L nozzle during a regularly
scheduled fire hose station flush.  The nozzle failed when it was pressurized
to nominal firemain pressure.  Following this event, the licensee replaced
Lexan-type HN-4-L nozzles with ball-style shutoff nozzles.

Discussion

During a fire hose pressurization test on August 3, 1992, the Lexan-
type HN-4-L nozzle attached to a hose being tested was shut to pressurize the
hose to the final test pressure of 1,756 kPa [254.7 psia].  With the hose
pressurized to approximately 1,204 kPa [174.7 psia], the nozzle failed.
Following a review of the event, the licensee revised their fire hose
hydrostatic test procedure to require the use of ball-style shutoff nozzles.
On June 17, 1993, a similar failure of a Lexan-type HN-4-L nozzle occurred
during a routine flush of an installed fire hose station.  With the nozzle
shut and the fire hose charged to the nominal system pressure of 1,032 kPa
[149.7 psia], the nozzle failed.


9404080170.                                        IN 94-31
                                        April 14, 1994
                                        Page 2 of 2


The nozzles were both 1 1/2-inch diameter, Lexan (polycarbonate) fog nozzles.
Originally, Wilco (Wilson and Cousins Company) manufactured these nozzles,
which are now manufactured by the A. Burks Pump Company.  They are designated
as Model HN-4-L and are approved by Factory Mutual Insurance Company for fire
hose station use.  The testing performed by Factory Mutual included a
hydrostatic test at 6,895 Kpa (1000 psi) and an operational test at pressures
up to 2,069 Kpa (300 psi).

Though the licensee does not track the installation of fire nozzles, it is
estimated that both nozzles had probably been in service for several years.
The nozzles consist of a stationary inner casing attached to the fire hose
fitting.  An outer shell is threaded onto this inner casing.  The outer shell
is twisted to adjust or start/stop flow.  In both of the failures, the inner
casing separated at the third land for the inner casing-outer shell thread.
No indications of imminent failure were present in either failure.  An
examination of the threaded area on some disassembled nozzles did not reveal
indications of cracking.

This information notice requires no specific action or written response.  If
you have any questions about the information in this notice, please contact
one of the technical contacts listed below or the appropriate Office of
Nuclear Reactor Regulation (NRR) project manager.

/S/'D BY CIGRIMES/FOR


                        Brian K. Grimes, Director
                        Division of Operating Reactor Support
                        Office of Nuclear Reactor Regulation

Technical contacts:  C. Ogle, RII
               (803) 383-4571

               W. Orders, RII
               (803) 383-4571

               P. Madden, NRR
                     (301) 504-2854

Attachment:
List of Recently Issued NRC Information Notices
```

*Page Last Reviewed/Updated Wednesday, February 16, 2011*

#### Home

            - News Releases
            - Event Reports
            - ADAMS
            - Open Gov
            - Students & Teachers
            - Photos & Video

#### About Us

            - Strategic Plan
            - Budget & Performance
            - Perf & Accountability Rept
            - History of the NRC
            - Employment
            - NRC Ethics
            - Agency Status

#### Popular Documents

            - Info Digest
            - Factsheets & Brochures
            - Forms
            - Electronic Submittals
            - NRC Reports – NUREG
            - NRC Regulations – 10-CFR
            - Inspection Reports

#### Follow Along

            - Blog
            - RSS

Regulations.govUSA.govExpectMore.govRecoveryFOIANo Fear EEOInspector GeneralSite MapAccessibilityPrivacy PolicySite DisclaimerFor Employees