Facility Name Unit ID Pollutant Run No. Flag ND Raw Data ND < Avg Ln-transformed Data

LAIPMansfield 2-78 - No. 2 Power Boiler Cadmium (Cd) LAIPMansfield2CdT1R2 0 1.59125E-05 N/A -11.04840807

LAIPMansfield 2-78 - No. 2 Power Boiler Cadmium (Cd) LAIPMansfield2CdT1R1 0 1.07062E-05 N/A -11.44468407

LAIPMansfield 2-78 - No. 2 Power Boiler Cadmium (Cd) LAIPMansfield2CdT1R3 0 0.000384271 N/A -7.864163422

MEHuberEngineeredWoodLLCBoiler No.1 Cadmium (Cd) 3 DLL 1 0.000147397 0.0001474 -8.822380619

MEHuberEngineeredWoodLLCBoiler No.1 Cadmium (Cd) 1 DLL 1 0.00016825 N/A -8.690059826

MEHuberEngineeredWoodLLCBoiler No.1 Cadmium (Cd) 2 DLL 1 0.000182293 N/A -8.609894994

ORGPToledo EU11 - Hog Fuel Boiler #4 Cadmium (Cd) M5-1E 0 0.00021 N/A -8.468403027

ORGPToledo EU11 - Hog Fuel Boiler #4 Cadmium (Cd) M5-2E 0 0.00019 N/A -8.568486486

ORGPToledo EU11 - Hog Fuel Boiler #4 Cadmium (Cd) M5-3E ND 1 0.00018 N/A -8.622553707

ORGPToledo EU11 - Hog Fuel Boiler #4 Cadmium (Cd) M5-3W 0 0.00012 N/A -9.028018815

ORGPToledo EU11 - Hog Fuel Boiler #4 Cadmium (Cd) M5-2W 0 0.0002 N/A -8.517193191

ORGPToledo EU11 - Hog Fuel Boiler #4 Cadmium (Cd) M5-1W 0 0.0002 N/A -8.517193191

Sample Size 12 12

Non-detects 4 4

Average 0.00017 -9.02

Median 0.00018 -8.62

Standard Deviation 0.00010 1.08

Minimum 0.00001 -11.44

Maximum 0.00038 -7.86

Skewness 0.36 -1.78

SE Skewness 0.71 0.71

Skewness Test Normal Normal

Kurtosis 2.11 2.22

SE Kurtosis 1.41 1.41

Kurtosis Test Normal Normal

99.0% t-statistic for UL 2.68 2.68

99.0% UL 0.0004 0.00

99.0% t-statistic for UPL 2.72 2.72

99.0% UPL 0.0003 0.000806

95.0% t-statistic for UL 1.78 1.78

95.0% UL 0.0003 0.0008

95.0% t-statistic for UPL 1.80 1.80

95.0% UPL 0.0003 0.0004

ND

Maximum ND: 1 0.0001823

Maximum ND less than average: 0.000147397

3x highest DL less than average 0.000442191

Page 1
Facility Name Unit ID Pollutant Run No. Flag ND Raw Data ND < Avg Ln-transformed Data

ARDomtarIndustries PB1 Carbon Monoxide (CO) Sample #1 0 100.442105 N/A 4.609581494

ARDomtarIndustries PB1 Carbon Monoxide (CO) Sample #2 0 124.442369 N/A 4.823842708

ARDomtarIndustries PB1 Carbon Monoxide (CO) Sample #3 0 95.1799572 N/A 4.555769386

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Carbon Monoxide (CO) 3 0 120 N/A 4.787491743

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Carbon Monoxide (CO) 2 0 150 N/A 5.010635294

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Carbon Monoxide (CO) 1 0 299 N/A 5.700443573

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Carbon Monoxide (CO) LAInternationalPaperRedRiverMillCOT1R1 0 116.4 N/A 4.757032535

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Carbon Monoxide (CO) LAInternationalPaperRedRiverMillCOT1R2 0 96.5 N/A 4.569543008

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Carbon Monoxide (CO) LAInternationalPaperRedRiverMillCOT1R3 0 107.3 N/A 4.67562865

ALIPRiverdale No. 2 Bark Boiler / BK02 Carbon Monoxide (CO) 1 0 127 N/A 4.844187086

ALIPRiverdale No. 2 Bark Boiler / BK02 Carbon Monoxide (CO) 2 0 205 N/A 5.323009979

ALIPRiverdale No. 2 Bark Boiler / BK02 Carbon Monoxide (CO) 3 0 269 N/A 5.59471138

ALIPRiverdale No. 2 Bark Boiler / BK02 Carbon Monoxide (CO) ALIPRiverdale2COT1R1 0 66.1 N/A 4.191168747

ALIPRiverdale No. 2 Bark Boiler / BK02 Carbon Monoxide (CO) ALIPRiverdale2COT1R2 0 123.8 N/A 4.81866736

ALIPRiverdale No. 2 Bark Boiler / BK02 Carbon Monoxide (CO) ALIPRiverdale2COT1R3 0 128.3 N/A 4.854371272

Sample Size 15 15

Non-detects 0 0

Average 141.89763 4.87

Median 123.80000 4.82

Standard Deviation 65.44176 0.40

Minimum 66.10000 4.19

Maximum 299.00000 5.70

Skewness 1.59 0.81

SE Skewness 0.63 0.63

Skewness Test Non-normal Normal

Kurtosis 1.82 0.68

SE Kurtosis 1.26 1.26

Kurtosis Test Normal Normal

99.0% t-statistic for UL 2.60 2.60

99.0% UL 312.2085 369.00

99.0% t-statistic for UPL 2.62 2.62

99.0% UPL 250.5228 253.5137

95.0% t-statistic for UL 1.75 1.75

95.0% UL 256.6203 263.0970

95.0% t-statistic for UPL 1.76 1.76

95.0% UPL 214.7965 203.9784

ND

Maximum ND: 1 0.0000000

Maximum ND less than average: N/A

3x highest DL less than average N/A

Raw Data are span-adjusted CO values.

Page 1
Facility Name Unit ID Pollutant Run No. Flag ND Raw Data ND < Avg Ln-transformed Data

ALIPRiverdale No. 2 Bark Boiler / BK02 Hydrogen Chloride (HCl) 3 0 0.115 N/A -2.162823151

ALIPRiverdale No. 2 Bark Boiler / BK02 Hydrogen Chloride (HCl) 2 0 0.153 N/A -1.877317358

ALIPRiverdale No. 2 Bark Boiler / BK02 Hydrogen Chloride (HCl) 1 0 0.124 N/A -2.087473713

TXInternationalPaperQueenCity PB02 Hydrogen Chloride (HCl) 3 ND 1 0.0425 0.0425 -3.158251203

TXInternationalPaperQueenCity PB02 Hydrogen Chloride (HCl) 2 0 0.0789 N/A -2.539574051

TXInternationalPaperQueenCity PB02 Hydrogen Chloride (HCl) 1 0 0.083 N/A -2.488914671

WINSPWAshland B20 Hydrogen Chloride (HCl) 3 0 0.09353914 N/A -2.369375321

WINSPWAshland B20 Hydrogen Chloride (HCl) 2 0 0.09953618 N/A -2.307234133

WINSPWAshland B20 Hydrogen Chloride (HCl) 1 0 0.10683273 N/A -2.236490986

Sample Size 9 9

Non-detects 1 1

Average 0.09959 -2.36

Median 0.09954 -2.31

Standard Deviation 0.03110 0.36

Minimum 0.04250 -3.16

Maximum 0.15300 -1.88

Skewness -0.15 -1.28

SE Skewness 0.82 0.82

Skewness Test Normal Normal

Kurtosis 0.99 2.75

SE Kurtosis 1.63 1.63

Kurtosis Test Normal Normal

99.0% t-statistic for UL 2.82 2.82

99.0% UL 0.1873 0.26

99.0% t-statistic for UPL 2.90 2.90

99.0% UPL 0.1596 0.1903

95.0% t-statistic for UL 1.83 1.83

95.0% UL 0.1566 0.1837

95.0% t-statistic for UPL 1.86 1.86

95.0% UPL 0.1381 0.1482

ND

Maximum ND: 1 0.0425000

Maximum ND less than average: 0.0425

3x highest DL less than average 0.1275

s

Page 1
Facility Name Unit ID Pollutant Run No. Flag ND Raw Data ND < Avg Ln-transformed Data

ALIPRiverdale No. 2 Bark Boiler / BK02 Lead (Pb) 2 0 0.000962 N/A -6.946496107

ALIPRiverdale No. 2 Bark Boiler / BK02 Lead (Pb) 1 0 0.00106 N/A -6.849486371

ALIPRiverdale No. 2 Bark Boiler / BK02 Lead (Pb) 3 0 0.00108 N/A -6.830794238

LAIPMansfield 2-78 - No. 2 Power Boiler Lead (Pb) LAIPMansfield2PbT1R3 0 0.00234832 N/A -6.054054815

LAIPMansfield 2-78 - No. 2 Power Boiler Lead (Pb) LAIPMansfield2PbT1R1 0 0.00246243 N/A -6.006604766

LAIPMansfield 2-78 - No. 2 Power Boiler Lead (Pb) LAIPMansfield2PbT1R2 0 0.00859273 N/A -4.756838933

MEHuberEngineeredWoodLLCBoiler No.1 Lead (Pb) 3 ADL 0 0.00057225 N/A -7.465939221

MEHuberEngineeredWoodLLCBoiler No.1 Lead (Pb) 2 ADL 0 0.00091147 N/A -7.000457081

MEHuberEngineeredWoodLLCBoiler No.1 Lead (Pb) 1 ADL 0 0.00116814 N/A -6.752346444

Sample Size 9 9

Non-detects 0 0

Average 0.00213 -6.52

Median 0.00108 -6.83

Standard Deviation 0.00251 0.80

Minimum 0.00057 -7.47

Maximum 0.00859 -4.76

Skewness 2.64 1.42

SE Skewness 0.82 0.82

Skewness Test Non-normal Normal

Kurtosis 7.31 2.30

SE Kurtosis 1.63 1.63

Kurtosis Test Non-normal Normal

99.0% t-statistic for UL 2.82 2.82

99.0% UL 0.0092 0.01

99.0% t-statistic for UPL 2.90 2.90

99.0% UPL 0.0070 0.00696

95.0% t-statistic for UL 1.83 1.83

95.0% UL 0.0067 0.0064

95.0% t-statistic for UPL 1.86 1.86

95.0% UPL 0.0052 0.0040

ND

Maximum ND: 1 0.0000000

Maximum ND less than average: N/A

3x highest DL less than average N/A

Page 1
Facility Name Unit ID Pollutant Run No. Flag ND Raw Data ND < Avg

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Mercury (Hg) 3 ND 1 0.000406 N/A

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Mercury (Hg) 1 ND 1 0.000416 N/A

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Mercury (Hg) 2 ND 1 0.000391 N/A

LAIPMansfield 2-78 - No. 2 Power Boiler Mercury (Hg) LAIPMansfield2HgT1R1 0 1.0706E-05 N/A

LAIPMansfield 2-78 - No. 2 Power Boiler Mercury (Hg) LAIPMansfield2HgT1R3 0 3.2023E-05 N/A

LAIPMansfield 2-78 - No. 2 Power Boiler Mercury (Hg) LAIPMansfield2HgT1R2 0 5.3042E-05 N/A

MEHuberEngineeredWoodLLC Boiler No.1 Mercury (Hg) 3 DLL 1 0.00017211 0.00017211

MEHuberEngineeredWoodLLC Boiler No.1 Mercury (Hg) 1 DLL 1 0.00037111 N/A

MEHuberEngineeredWoodLLC Boiler No.1 Mercury (Hg) 2 DLL 1 0.00041421 N/A

Sample Size 9

Non-detects 6

Average 0.00025

Median 0.00037

Standard Deviation 0.00018

Minimum 0.00001

Maximum 0.00042

Skewness -0.44

SE Skewness 0.82

Skewness Test Normal

Kurtosis -2.12

SE Kurtosis 1.63

Kurtosis Test Normal

99.0% t-statistic for UL 2.82

99.0% UL 0.0008

99.0% t-statistic for UPL 2.90

99.0% UPL 0.0006

95.0% t-statistic for UL 1.83

95.0% UL 0.0006

95.0% t-statistic for UPL 1.86

95.0% UPL 0.0005

ND

Maximum ND: 1 0.0004160

Maximum ND less than average: 0.00017211

3x highest DL less than average 0.00051632

Page 1
Ln-transformed Data

-7.809157398

-7.784825298

-7.846802998

-11.44468407

-10.34907007

-9.844435268

-8.667389956

-7.89900843

-7.789136688

9

6

-8.83

-7.90

1.38

-11.44

-7.78

-1.07

0.82

Normal

-0.26

1.63

Normal

2.82

0.01

2.90

0.0021

1.83

0.0018

1.86

0.0008

Page 2
Facility Name Unit ID Pollutant Run No. Flag ND Raw Data ND < Avg Ln-transformed Data

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Nitrogen Oxides (NOx) LAInternationalPaperRedRiverMillNOxT1R1 0 20.68 N/A 3.02916705

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Nitrogen Oxides (NOx) LAInternationalPaperRedRiverMillNOxT1R2 0 25.49 N/A 3.238286218

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Nitrogen Oxides (NOx) LAInternationalPaperRedRiverMillNOxT1R3 0 21.77 N/A 3.080532875

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Nitrogen Oxides (NOx) 1 0 122 N/A 4.804021045

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Nitrogen Oxides (NOx) 2 0 86 N/A 4.454347296

LAInternationalPaperRedRiverMill EQT011 Hogged Fuel Boiler No. 2 Nitrogen Oxides (NOx) 3 0 98 N/A 4.584967479

MEHuberEngineeredWoodLLC Boiler No.1 Nitrogen Oxides (NOx) 1 0 123.901251 N/A 4.819484884

MEHuberEngineeredWoodLLC Boiler No.1 Nitrogen Oxides (NOx) 2 0 127.618792 N/A 4.849047632

MEHuberEngineeredWoodLLC Boiler No.1 Nitrogen Oxides (NOx) 3 0 121.643543 N/A 4.801094991

OKIPValliant Bark Boiler EUG-D1 Nitrogen Oxides (NOx) 1 0 135.37 N/A 4.90801177

OKIPValliant Bark Boiler EUG-D1 Nitrogen Oxides (NOx) 2 0 22.56 N/A 3.116178427

OKIPValliant Bark Boiler EUG-D1 Nitrogen Oxides (NOx) 3 0 136.08 N/A 4.913242948

Sample Size 12 12

Non-detects 0 0

Average 86.75947 4.22

Median 109.82177 4.69

Standard Deviation 49.44773 0.82

Minimum 20.68000 3.03

Maximum 136.08000 4.91

Skewness -0.56 -0.74

SE Skewness 0.71 0.71

Skewness Test Normal Normal

Kurtosis -1.73 -1.63

SE Kurtosis 1.41 1.41

Kurtosis Test Normal Normal

99.0% t-statistic for UL 2.68 2.68

99.0% UL 219.3287 618.02

99.0% t-statistic for UPL 2.72 2.72

99.0% UPL 173.5161 287.9536

95.0% t-statistic for UL 1.78 1.78

95.0% UL 174.8895 294.6224

95.0% t-statistic for UPL 1.80 1.80

95.0% UPL 144.0812 176.2859

ND

Maximum ND: 1 0.0000000

Maximum ND less than average: N/A

3x highest DL less than average N/A

Page 1
Facility Name Unit ID Pollutant Run No. Flag ND Raw Data ND < Avg Ln-transformed Data

ALIPRiverdale No. 2 Bark Boiler / BK02 Particulate Matter (filterable) 3 0 3.4 N/A 1.223775432

ALIPRiverdale No. 2 Bark Boiler / BK02 Particulate Matter (filterable) 2 0 2.99 N/A 1.095273387

ALIPRiverdale No. 2 Bark Boiler / BK02 Particulate Matter (filterable) 1 0 3.42 N/A 1.229640551

MEHuberEngineeredWoodLLC Boiler No.1 Particulate Matter (filterable) 3 0 5.50571319 N/A 1.705786315

MEHuberEngineeredWoodLLC Boiler No.1 Particulate Matter (filterable) 1 0 3.55728487 N/A 1.268997578

MEHuberEngineeredWoodLLC Boiler No.1 Particulate Matter (filterable) 2 0 5.01305891 N/A 1.61204629

WALongviewFPP #20 Power Boiler Particulate Matter (filterable) WALongviewFPP-20-PMfiltT1aR2 0 5.7 N/A 1.740466175

WALongviewFPP #20 Power Boiler Particulate Matter (filterable) WALongviewFPP-20-PMfiltT1aR1 0 5.7 N/A 1.740466175

WALongviewFPP #20 Power Boiler Particulate Matter (filterable) WALongviewFPP-20-PMfiltT1bR2 0 13 N/A 2.564949357

WALongviewFPP #20 Power Boiler Particulate Matter (filterable) WALongviewFPP-20-PMfiltT1bR1 0 14.2 N/A 2.653241965

WALongviewFPP #20 Power Boiler Particulate Matter (filterable) 3-N 0 3.10780674 N/A 1.133917249

WALongviewFPP #20 Power Boiler Particulate Matter (filterable) 2-N 0 3.65300728 N/A 1.295550742

WALongviewFPP #20 Power Boiler Particulate Matter (filterable) 1-N 0 3.88073791 N/A 1.356025319

WALongviewFPP #20 Power Boiler Particulate Matter (filterable) 2-S 0 7.04128523 N/A 1.951790715

WALongviewFPP #20 Power Boiler Particulate Matter (filterable) 1-S 0 3.20846564 N/A 1.165792828

WALongviewFPP #20 Power Boiler Particulate Matter (filterable) 3-S 0 3.09070451 N/A 1.12839906

Sample Size 16 16

Non-detects 0 0

Average 5.40425 1.55

Median 3.76687 1.33

Standard Deviation 3.42645 0.49

Minimum 2.99000 1.10

Maximum 14.20000 2.65

Skewness 1.98 1.30

SE Skewness 0.61 0.61

Skewness Test Non-normal Non-normal

Kurtosis 3.15 0.95

SE Kurtosis 1.22 1.22

Kurtosis Test Non-normal Normal

99.0% t-statistic for UL 2.58 2.58

99.0% UL 14.2564 16.7871

99.0% t-statistic for UPL 2.60 2.60

99.0% UPL 11.0146 10.5571

95.0% t-statistic for UL 1.75 1.75

95.0% UL 11.3864 11.1340

95.0% t-statistic for UPL 1.75 1.75

95.0% UPL 9.1834 8.1239

ND

Maximum ND: 1 0.0000000

Maximum ND less than average: N/A

3x highest DL less than average N/A

Page 1
Facility Name Unit ID Pollutant Run No. Flag ND Raw Data ND < Avg Ln-transformed Data

ALIPRiverdale No. 2 Bark Boiler / BK02 Sulfur Dioxide (SO2) ALIPRiverdale2SO2T1R1 0 5.4 N/A 1.686398954

ALIPRiverdale No. 2 Bark Boiler / BK02 Sulfur Dioxide (SO2) ALIPRiverdale2SO2T1R2 0 4.3 N/A 1.458615023

ALIPRiverdale No. 2 Bark Boiler / BK02 Sulfur Dioxide (SO2) ALIPRiverdale2SO2T1R3 0 4 N/A 1.386294361

MEHuberEngineeredWoodLLC Boiler No.1 Sulfur Dioxide (SO2) 1 0 2.92824226 N/A 1.074402333

MEHuberEngineeredWoodLLC Boiler No.1 Sulfur Dioxide (SO2) 2 0 0.93288591 N/A -0.069472373

MEHuberEngineeredWoodLLC Boiler No.1 Sulfur Dioxide (SO2) 3 0 2.22518677 N/A 0.799840852

OKIPValliant Bark Boiler EUG-D1 Sulfur Dioxide (SO2) 1 0 2.505 N/A 0.918288735

OKIPValliant Bark Boiler EUG-D1 Sulfur Dioxide (SO2) 2 0 1.823 N/A 0.600483496

OKIPValliant Bark Boiler EUG-D1 Sulfur Dioxide (SO2) 3 0 2.242 N/A 0.807368325

Sample Size 9 9

Non-detects 0 0

Average 2.92848 0.96

Median 2.50500 0.92

Standard Deviation 1.39137 0.53

Minimum 0.93289 -0.07

Maximum 5.40000 1.69

Skewness 0.53 -0.64

SE Skewness 0.82 0.82

Skewness Test Normal Normal

Kurtosis -0.28 0.76

SE Kurtosis 1.63 1.63

Kurtosis Test Normal Normal

99.0% t-statistic for UL 2.82 2.82

99.0% UL 6.8541 11.54

99.0% t-statistic for UPL 2.90 2.90

99.0% UPL 5.6152 7.2251

95.0% t-statistic for UL 1.83 1.83

95.0% UL 5.4790 6.8628

95.0% t-statistic for UPL 1.86 1.86

95.0% UPL 4.6534 5.0237

ND

Maximum ND: 1 0.0000000

Maximum ND less than average: N/A

3x highest DL less than average N/A

Page 1
Facility Name Unit ID Pollutant Run No. Flag ND Raw Data ND < Avg Ln-transformed Data

17 x TMB DL 

Average Run 

Value

TMB DL 

<Avg

Congener Data 

Available?

ALIPRiverdale No. 2 Bark Boiler / BK02 Total Dioxin/Furans 1 ND 1 0.0661 0.0661 -2.716586532 0.037343333 0.03734 Y

ALIPRiverdale No. 2 Bark Boiler / BK02 Total Dioxin/Furans 2 ND 1 0.0608 0.0608 -2.80016549 0.015853444 0.01585 Y

ALIPRiverdale No. 2 Bark Boiler / BK02 Total Dioxin/Furans 3 ND 1 0.0838 0.0838 -2.479322271 10.24684736 N/A Y

MEHuberEngineeredWoodLLC Boiler No.1 Total Dioxin/Furans 1 BDL 1 0.08176808 0.08176808 -2.503868295 0.048573484 0.04857 Y

MEHuberEngineeredWoodLLC Boiler No.1 Total Dioxin/Furans 2 BDL 1 0.1827243 N/A -1.699776836 0.07271598 0.07272 Y

MEHuberEngineeredWoodLLC Boiler No.1 Total Dioxin/Furans 3 BDL 1 0.08497486 0.08497486 -2.465399831 0.054910501 0.05491 Y

WINSPWAshland B20 Total Dioxin/Furans 1 DLL 1 0.42 N/A -0.867500568 Y

WINSPWAshland B20 Total Dioxin/Furans 2 DLL 1 0.09 0.09 -2.407945609 Y

WINSPWAshland B20 Total Dioxin/Furans 3 DLL 1 0.13 0.13 -2.040220829 Y

Sample Size 9 9

Non-detects 9 9

Average 0.13335 -2.22

Median 0.08497 -2.47

Standard Deviation 0.11387 0.61

Minimum 0.06080 -2.80

Maximum 0.42000 -0.87

Skewness 2.45 1.60

SE Skewness 0.82 0.82

Skewness Test Non-normal Normal

Kurtosis 6.30 2.50

SE Kurtosis 1.63 1.63

Kurtosis Test Non-normal Normal

99.0% t-statistic for UL 2.82 2.82

99.0% UL 0.4546 0.60

99.0% t-statistic for UPL 2.90 2.90

99.0% UPL 0.3532 0.3514

95.0% t-statistic for UL 1.83 1.83

95.0% UL 0.3421 0.3311

95.0% t-statistic for UPL 1.86 1.86

95.0% UPL 0.2745 0.2308

Maximum TMB DL less than average: 0.07271598

3x Max TMB DL less than average: 0.21814794

Page 1
Facility ID Combustion Unit ID Run ID Test ID Pollutant

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,6,7,8 HpCDD-8/2009 1 1,2,3,4,6,7,8 HpCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,6,7,8 HpCDF-8/2009 1 1,2,3,4,6,7,8 HpCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,6,5,7,8 OCDD-8/2009 1 1,2,3,4,6,7,8,9 OCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,6,5,7,8 OCDF-8/2009 1 1,2,3,4,6,7,8,9 OCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,7,8 HxCDD-8/2009 1 1,2,3,4,7,8 HxCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,7,8 HxCDF-8/2009 1 1,2,3,4,7,8 HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,7,8,9 HpCDF-8/2009 1 1,2,3,4,7,8,9 HpCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,6,7,8 HxCDD-8/2009 1 1,2,3,6,7,8 HxCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,6,7,8 HxCDF-8/2009 1 1,2,3,6,7,8 HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,7,8 PeCDD-8/2009 1 1,2,3,7,8 PeCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,7,8 PeCDF-8/2009 1 1,2,3,7,8 PeCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,7,8,9 HxCDD-8/2009 1 1,2,3,7,8,9 HxCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,7,8,9 HxCDF-8/2009 1 1,2,3,7,8,9 HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 2,3,4,6,7,8 HxCDF-8/2009 1 2,3,4,6,7,8 HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 2,3,4,7,8 PeCDF-8/2009 1 2,3,4,7,8 PeCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 2,3,7,8 TCDD-8/2009 1 2,3,7,8 TCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 2,3,7,8 TCDF-8/2009 1 2,3,7,8 TCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 Other HpCDD-8/2009 1 Other HpCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 Other HpCDF-8/2009 1 Other HpCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 Other HxCDD-8/2009 1 Other HxCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 Other HxCDF-8/2009 1 Other HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 Other PeCDD-8/2009 1 Other PeCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 Other PeCDF-8/2009 1 Other PeCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 Other TCDD-8/2009 1 Other TCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 Other TCDF-8/2009 1 Other TCDF

ALIPRiverdaleNo. 2 Bark Boiler / BK02 Total Dioxin/Furans-8/2009 1 Total Dioxin/Furans

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,6,7,8 HpCDD-8/2009 2 1,2,3,4,6,7,8 HpCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,6,7,8 HpCDF-8/2009 2 1,2,3,4,6,7,8 HpCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,6,5,7,8 OCDD-8/2009 2 1,2,3,4,6,7,8,9 OCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,6,5,7,8 OCDF-8/2009 2 1,2,3,4,6,7,8,9 OCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,7,8 HxCDD-8/2009 2 1,2,3,4,7,8 HxCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,7,8 HxCDF-8/2009 2 1,2,3,4,7,8 HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,7,8,9 HpCDF-8/2009 2 1,2,3,4,7,8,9 HpCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,6,7,8 HxCDD-8/2009 2 1,2,3,6,7,8 HxCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,6,7,8 HxCDF-8/2009 2 1,2,3,6,7,8 HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,7,8 PeCDD-8/2009 2 1,2,3,7,8 PeCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,7,8 PeCDF-8/2009 2 1,2,3,7,8 PeCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,7,8,9 HxCDD-8/2009 2 1,2,3,7,8,9 HxCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,7,8,9 HxCDF-8/2009 2 1,2,3,7,8,9 HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 2,3,4,6,7,8 HxCDF-8/2009 2 2,3,4,6,7,8 HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 2,3,4,7,8 PeCDF-8/2009 2 2,3,4,7,8 PeCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 2,3,7,8 TCDD-8/2009 2 2,3,7,8 TCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 2,3,7,8 TCDF-8/2009 2 2,3,7,8 TCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 Other HpCDD-8/2009 2 Other HpCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 Other HpCDF-8/2009 2 Other HpCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 Other HxCDD-8/2009 2 Other HxCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 Other HxCDF-8/2009 2 Other HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 Other PeCDD-8/2009 2 Other PeCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 Other PeCDF-8/2009 2 Other PeCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 Other TCDD-8/2009 2 Other TCDD
ALIPRiverdale No. 2 Bark Boiler / BK02 Other TCDF-8/2009 2 Other TCDF

ALIPRiverdaleNo. 2 Bark Boiler / BK02 Total Dioxin/Furans-8/2009 2 Total Dioxin/Furans

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,6,7,8 HpCDD-8/2009 3 1,2,3,4,6,7,8 HpCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,6,7,8 HpCDF-8/2009 3 1,2,3,4,6,7,8 HpCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,6,5,7,8 OCDD-8/2009 3 1,2,3,4,6,7,8,9 OCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,6,5,7,8 OCDF-8/2009 3 1,2,3,4,6,7,8,9 OCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,7,8 HxCDD-8/2009 3 1,2,3,4,7,8 HxCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,7,8 HxCDF-8/2009 3 1,2,3,4,7,8 HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,4,7,8,9 HpCDF-8/2009 3 1,2,3,4,7,8,9 HpCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,6,7,8 HxCDD-8/2009 3 1,2,3,6,7,8 HxCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,6,7,8 HxCDF-8/2009 3 1,2,3,6,7,8 HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,7,8 PeCDD-8/2009 3 1,2,3,7,8 PeCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,7,8 PeCDF-8/2009 3 1,2,3,7,8 PeCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,7,8,9 HxCDD-8/2009 3 1,2,3,7,8,9 HxCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 1,2,3,7,8,9 HxCDF-8/2009 3 1,2,3,7,8,9 HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 2,3,4,6,7,8 HxCDF-8/2009 3 2,3,4,6,7,8 HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 2,3,4,7,8 PeCDF-8/2009 3 2,3,4,7,8 PeCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 2,3,7,8 TCDD-8/2009 3 2,3,7,8 TCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 2,3,7,8 TCDF-8/2009 3 2,3,7,8 TCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 Other HpCDD-8/2009 3 Other HpCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 Other HpCDF-8/2009 3 Other HpCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 Other HxCDD-8/2009 3 Other HxCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 Other HxCDF-8/2009 3 Other HxCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 Other PeCDD-8/2009 3 Other PeCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 Other PeCDF-8/2009 3 Other PeCDF

ALIPRiverdale No. 2 Bark Boiler / BK02 Other TCDD-8/2009 3 Other TCDD

ALIPRiverdale No. 2 Bark Boiler / BK02 Other TCDF-8/2009 3 Other TCDF

ALIPRiverdaleNo. 2 Bark Boiler / BK02 Total Dioxin/Furans-8/2009 3 Total Dioxin/Furans

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,6,7,8 HpCDD-9/2009 1 1,2,3,4,6,7,8 HpCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,6,7,8 HpCDF-9/2009 1 1,2,3,4,6,7,8 HpCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,7,8 HxCDD-9/2009 1 1,2,3,4,7,8 HxCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,7,8 HxCDF-9/2009 1 1,2,3,4,7,8 HxCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,7,8,9 HpCDF-9/2009 1 1,2,3,4,7,8,9 HpCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,6,7,8 HxCDD-9/2009 1 1,2,3,6,7,8 HxCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,6,7,8 HxCDF-9/2009 1 1,2,3,6,7,8 HxCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,7,8 PeCDD-9/2009 1 1,2,3,7,8 PeCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,7,8 PeCDF-9/2009 1 1,2,3,7,8 PeCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,7,8,9 HxCDD-9/2009 1 1,2,3,7,8,9 HxCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,7,8,9 HxCDF-9/2009 1 1,2,3,7,8,9 HxCDF

MEHuberEngineeredW Boiler No.1 oodLLC 2,3,4,6,7,8 HxCDF-9/2009 1 2,3,4,6,7,8 HxCDF

MEHuberEngineeredW Boiler No.1 oodLLC 2,3,4,7,8 PeCDF-9/2009 1 2,3,4,7,8 PeCDF

MEHuberEngineeredW Boiler No.1 oodLLC 2,3,7,8 TCDD-9/2009 1 2,3,7,8 TCDD

MEHuberEngineeredW Boiler No.1 oodLLC 2,3,7,8 TCDF-9/2009 1 2,3,7,8 TCDF

MEHuberEngineeredW Boiler No.1 oodLLC Total OCDD-9/2009 1 Total OCDD

MEHuberEngineeredW Boiler No.1 oodLLC Total OCDF-9/2009 1 Total OCDF

MEHuberEngineeredWoodLLC Boiler No.1 Total Dioxin/Furans-9/2009 1 Total Dioxin/Furans

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,6,7,8 HpCDD-9/2009 2 1,2,3,4,6,7,8 HpCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,6,7,8 HpCDF-9/2009 2 1,2,3,4,6,7,8 HpCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,7,8 HxCDD-9/2009 2 1,2,3,4,7,8 HxCDD
MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,7,8 HxCDF-9/2009 2 1,2,3,4,7,8 HxCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,7,8,9 HpCDF-9/2009 2 1,2,3,4,7,8,9 HpCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,6,7,8 HxCDD-9/2009 2 1,2,3,6,7,8 HxCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,6,7,8 HxCDF-9/2009 2 1,2,3,6,7,8 HxCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,7,8 PeCDD-9/2009 2 1,2,3,7,8 PeCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,7,8 PeCDF-9/2009 2 1,2,3,7,8 PeCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,7,8,9 HxCDD-9/2009 2 1,2,3,7,8,9 HxCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,7,8,9 HxCDF-9/2009 2 1,2,3,7,8,9 HxCDF

MEHuberEngineeredW Boiler No.1 oodLLC 2,3,4,6,7,8 HxCDF-9/2009 2 2,3,4,6,7,8 HxCDF

MEHuberEngineeredW Boiler No.1 oodLLC 2,3,4,7,8 PeCDF-9/2009 2 2,3,4,7,8 PeCDF

MEHuberEngineeredW Boiler No.1 oodLLC 2,3,7,8 TCDD-9/2009 2 2,3,7,8 TCDD

MEHuberEngineeredW Boiler No.1 oodLLC 2,3,7,8 TCDF-9/2009 2 2,3,7,8 TCDF

MEHuberEngineeredW Boiler No.1 oodLLC Total OCDD-9/2009 2 Total OCDD

MEHuberEngineeredW Boiler No.1 oodLLC Total OCDF-9/2009 2 Total OCDF

MEHuberEngineeredWoodLLC Boiler No.1 Total Dioxin/Furans-9/2009 2 Total Dioxin/Furans

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,6,7,8 HpCDD-9/2009 3 1,2,3,4,6,7,8 HpCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,6,7,8 HpCDF-9/2009 3 1,2,3,4,6,7,8 HpCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,7,8 HxCDD-9/2009 3 1,2,3,4,7,8 HxCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,7,8 HxCDF-9/2009 3 1,2,3,4,7,8 HxCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,4,7,8,9 HpCDF-9/2009 3 1,2,3,4,7,8,9 HpCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,6,7,8 HxCDD-9/2009 3 1,2,3,6,7,8 HxCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,6,7,8 HxCDF-9/2009 3 1,2,3,6,7,8 HxCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,7,8 PeCDD-9/2009 3 1,2,3,7,8 PeCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,7,8 PeCDF-9/2009 3 1,2,3,7,8 PeCDF

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,7,8,9 HxCDD-9/2009 3 1,2,3,7,8,9 HxCDD

MEHuberEngineeredW Boiler No.1 oodLLC 1,2,3,7,8,9 HxCDF-9/2009 3 1,2,3,7,8,9 HxCDF

MEHuberEngineeredW Boiler No.1 oodLLC 2,3,4,6,7,8 HxCDF-9/2009 3 2,3,4,6,7,8 HxCDF

MEHuberEngineeredW Boiler No.1 oodLLC 2,3,4,7,8 PeCDF-9/2009 3 2,3,4,7,8 PeCDF

MEHuberEngineeredW Boiler No.1 oodLLC 2,3,7,8 TCDD-9/2009 3 2,3,7,8 TCDD

MEHuberEngineeredW Boiler No.1 oodLLC 2,3,7,8 TCDF-9/2009 3 2,3,7,8 TCDF

MEHuberEngineeredW Boiler No.1 oodLLC Total OCDD-9/2009 3 Total OCDD

MEHuberEngineeredW Boiler No.1 oodLLC Total OCDF-9/2009 3 Total OCDF

MEHuberEngineeredWoodLLC Boiler No.1 Total Dioxin/Furans-9/2009 3 Total Dioxin/Furans
Dates Tested Non Detect? ND Count Emissions Normalized Normalized Units (7%O2) TEFvalue_05

06-Aug-09 0 0.00272 ng/dscm @ 7% O2 0.01

06-Aug-09 ND 1 0.00356 ng/dscm @ 7% O2 0.01

06-Aug-09 0 0.0065 ng/dscm @ 7% O2 0.0003

06-Aug-09 0 0.00512 ng/dscm @ 7% O2 0.0003

06-Aug-09 0 0.00116 ng/dscm @ 7% O2 0.1

06-Aug-09 0 0.0019 ng/dscm @ 7% O2 0.1

06-Aug-09 ND 1 0.00183 ng/dscm @ 7% O2 0.01

06-Aug-09 ND 1 0.00138 ng/dscm @ 7% O2 0.1

06-Aug-09 0 0.00171 ng/dscm @ 7% O2 0.1

06-Aug-09 0 0.00174 ng/dscm @ 7% O2 1

06-Aug-09 0 0.00196 ng/dscm @ 7% O2 0.03

06-Aug-09 ND 1 0.00125 ng/dscm @ 7% O2 0.1

06-Aug-09 0 0.00196 ng/dscm @ 7% O2 0.1

06-Aug-09 0 0.00183 ng/dscm @ 7% O2 0.1

06-Aug-09 0 0.00178 ng/dscm @ 7% O2 0.3

06-Aug-09 ND 1 0.00142 ng/dscm @ 7% O2 1

06-Aug-09 ND 1 0.00374 ng/dscm @ 7% O2 1

06-Aug-09 0 0.00334 ng/dscm @ 7% O2 0

06-Aug-09 0 0 ng/dscm @ 7% O2 0

06-Aug-09 0 0 ng/dscm @ 7% O2 0

06-Aug-09 0 0.000882 ng/dscm @ 7% O2 0

06-Aug-09 0 0 ng/dscm @ 7% O2 0

06-Aug-09 0 0.00138 ng/dscm @ 7% O2 0

06-Aug-09 0 0.000935 ng/dscm @ 7% O2 0

06-Aug-09 0 0.018 ng/dscm @ 7% O2 0

06-Aug-09 ND 1 0.0661 ng/dscm @ 7% O2

ND Count Emissions Normalized

06-Aug-09 ND 1 0.00173 ng/dscm @ 7% O2 0.01

06-Aug-09 ND 1 0.00178 ng/dscm @ 7% O2 0.01

06-Aug-09 0 0.00653 ng/dscm @ 7% O2 0.0003

06-Aug-09 0 0.002 ng/dscm @ 7% O2 0.0003

06-Aug-09 ND 1 0.000577 ng/dscm @ 7% O2 0.1

06-Aug-09 0 0.00107 ng/dscm @ 7% O2 0.1

06-Aug-09 ND 1 0.000622 ng/dscm @ 7% O2 0.01

06-Aug-09 0 0.00071 ng/dscm @ 7% O2 0.1

06-Aug-09 ND 1 0.000932 ng/dscm @ 7% O2 0.1

06-Aug-09 ND 1 0.000488 ng/dscm @ 7% O2 1

06-Aug-09 ND 1 0.000799 ng/dscm @ 7% O2 0.03

06-Aug-09 ND 1 0.000755 ng/dscm @ 7% O2 0.1

06-Aug-09 0 0.000888 ng/dscm @ 7% O2 0.1

06-Aug-09 0 0.000755 ng/dscm @ 7% O2 0.1

06-Aug-09 0 0.00124 ng/dscm @ 7% O2 0.3

06-Aug-09 ND 1 0.00071 ng/dscm @ 7% O2 1

06-Aug-09 0 0.00435 ng/dscm @ 7% O2 1

06-Aug-09 0 0.00164 ng/dscm @ 7% O2 0

06-Aug-09 0 0 ng/dscm @ 7% O2 0

06-Aug-09 0 0.000666 ng/dscm @ 7% O2 0

06-Aug-09 0 0 ng/dscm @ 7% O2 0

06-Aug-09 ND 1 0.00124 ng/dscm @ 7% O2 0

06-Aug-09 0 0.00244 ng/dscm @ 7% O2 0

06-Aug-09 0 0.00213 ng/dscm @ 7% O2 0
06-Aug-09

0 0.0268 ng/dscm @ 7% O20

06-Aug-09 ND1 0.0608 ng/dscm @ 7% O2

ND Count Emissions Normalized

06-Aug-09 ND1 0.00178 ng/dscm @ 7% O2 0.01

06-Aug-09 ND1 0.00166 ng/dscm @ 7% O2 0.01

06-Aug-090 0.00782 ng/dscm @ 7% O2 0.0003

06-Aug-090 0.00195 ng/dscm @ 7% O2 0.0003

06-Aug-09 ND1 0.000828 ng/dscm @ 7% O2 0.1

06-Aug-09 ND1 0.00108 ng/dscm @ 7% O2 0.1

06-Aug-09 ND1 0.000704 ng/dscm @ 7% O2 0.01

06-Aug-090 0.000745 ng/dscm @ 7% O2 0.1

06-Aug-09 ND1 0.000952 ng/dscm @ 7% O2 0.1

06-Aug-09 ND1 0.000952 ng/dscm @ 7% O21

06-Aug-09 ND1 0.00124 ng/dscm @ 7% O2 0.03

06-Aug-09 ND1 0.000455 ng/dscm @ 7% O2 0.1

06-Aug-09 ND1 0.000662 ng/dscm @ 7% O2 0.1

06-Aug-090 0.000869 ng/dscm @ 7% O2 0.1

06-Aug-090 0.00186 ng/dscm @ 7% O2 0.3

06-Aug-09 ND1 6.62 ng/dscm @ 7% O21

06-Aug-090 0.006 ng/dscm @ 7% O21

06-Aug-090 0.00244 ng/dscm @ 7% O20

06-Aug-0900 ng/dscm @ 7% O20

06-Aug-0900 ng/dscm @ 7% O20

06-Aug-090 0.00103 ng/dscm @ 7% O20

06-Aug-09 ND1 0.000952 ng/dscm @ 7% O20

06-Aug-090 0.00679 ng/dscm @ 7% O20

06-Aug-090 0.00327 ng/dscm @ 7% O20

06-Aug-090 0.0391 ng/dscm @ 7% O20

06-Aug-09 ND1 0.0838 ng/dscm @ 7% O2

ND Count Emissions Normalized

02-Sep-09 DLL1 0.003486379 ng/dscm @ 7% O2 0.01

02-Sep-09 DLL1 0.001495333 ng/dscm @ 7% O2 0.01

02-Sep-09 BDL1 0.004260675 ng/dscm @ 7% O2 0.1

02-Sep-09 BDL1 0.002363855 ng/dscm @ 7% O2 0.1

02-Sep-09 BDL1 0.001683786 ng/dscm @ 7% O2 0.01

02-Sep-09 BDL1 0.002986569 ng/dscm @ 7% O2 0.1

02-Sep-09 BDL1 0.001753432 ng/dscm @ 7% O2 0.1

02-Sep-09 BDL1 0.003711703 ng/dscm @ 7% O21

02-Sep-09 BDL1 0.002888246 ng/dscm @ 7% O2 0.03

02-Sep-09 BDL1 0.003506863 ng/dscm @ 7% O2 0.1

02-Sep-09 BDL1 0.002466275 ng/dscm @ 7% O2 0.1

02-Sep-09 BDL1 0.0023065 ng/dscm @ 7% O2 0.1

02-Sep-09 BDL1 0.002982472 ng/dscm @ 7% O2 0.3

02-Sep-09 BDL1 0.002859568 ng/dscm @ 7% O21

02-Sep-09 DLL1 0.00249905 ng/dscm @ 7% O21

02-Sep-09 ADL0 0.036051863 ng/dscm @ 7% O2 0.0003

02-Sep-09 BDL1 0.004465515 ng/dscm @ 7% O2 0.0003

02-Sep-09 BDL1 0.081768083 ng/dscm @ 7% O2

ND Count Emissions Normalized

03-Sep-09 ADL0 0.016548736 ng/dscm @ 7% O2 0.01

03-Sep-09 ADL0 0.014679047 ng/dscm @ 7% O2 0.01

03-Sep-09 BDL1 0.004654332 ng/dscm @ 7% O2 0.1
03-Sep-09 ADL 0 0.009109761 ng/dscm @ 7% O2 0.1

03-Sep-09 BDL 1 0.002717016 ng/dscm @ 7% O2 0.01

03-Sep-09 DLL 1 0.001877645 ng/dscm @ 7% O2 0.1

03-Sep-09 ADL 0 0.005927312 ng/dscm @ 7% O2 0.1

03-Sep-09 BDL 1 0.005688628 ng/dscm @ 7% O2 1

03-Sep-09 BDL 1 0.002884095 ng/dscm @ 7% O2 0.03

03-Sep-09 BDL 1 0.003830873 ng/dscm @ 7% O2 0.1

03-Sep-09 BDL 1 0.002884095 ng/dscm @ 7% O2 0.1

03-Sep-09 BDL 1 0.002701104 ng/dscm @ 7% O2 0.1

03-Sep-09 BDL 1 0.007916342 ng/dscm @ 7% O2 0.3

03-Sep-09 BDL 1 0.003206318 ng/dscm @ 7% O2 1

03-Sep-09 BDL 1 0.007279852 ng/dscm @ 7% O2 1

03-Sep-09 ADL 0 0.085130515 ng/dscm @ 7% O2 0.0003

03-Sep-09 BDL 1 0.005688628 ng/dscm @ 7% O2 0.0003

03-Sep-09 BDL 1 0.182724297 ng/dscm @ 7% O2

ND Count Emissions Normalized

03-Sep-09 DLL 1 0.004779887 ng/dscm @ 7% O2 0.01

03-Sep-09 DLL 1 0.002348738 ng/dscm @ 7% O2 0.01

03-Sep-09 BDL 1 0.005233153 ng/dscm @ 7% O2 0.1

03-Sep-09 BDL 1 0.002777279 ng/dscm @ 7% O2 0.1

03-Sep-09 BDL 1 0.001767734 ng/dscm @ 7% O2 0.01

03-Sep-09 BDL 1 0.003663207 ng/dscm @ 7% O2 0.1

03-Sep-09 BDL 1 0.002060296 ng/dscm @ 7% O2 0.1

03-Sep-09 DLL 1 0.003325318 ng/dscm @ 7% O2 1

03-Sep-09 BDL 1 0.003564313 ng/dscm @ 7% O2 0.03

03-Sep-09 BDL 1 0.004285416 ng/dscm @ 7% O2 0.1

03-Sep-09 BDl 1 0.002896777 ng/dscm @ 7% O2 0.1

03-Sep-09 DLL 1 0.001306228 ng/dscm @ 7% O2 0.1

03-Sep-09 BDL 1 0.003679689 ng/dscm @ 7% O2 0.3

03-Sep-09 BDL 1 0.003321198 ng/dscm @ 7% O2 1

03-Sep-09 DLL 1 0.003181097 ng/dscm @ 7% O2 1

03-Sep-09 ADL 0 0.033294388 ng/dscm @ 7% O2 0.0003

03-Sep-09 DLL 1 0.003490142 ng/dscm @ 7% O2 0.0003

03-Sep-09 DLL 1 0.08497486 ng/dscm @ 7% O2

ND Count

1
DL Average Run (TMB)

0.002196667
0.000932556

0.602755727

0.002857264
0.004277411

0.003230029
Facility Name Unit ID Pollutant Run No. Flag ND Raw Data ND < Avg Ln-transformed Data

TEQDL average 

run value TEQDL <Avg Congener Data Available?

LAIPMansfield 2-78 - No. 2 Power Boiler Total Dioxin/Furans (TEQ) 1 0 0.0150428 N/A -4.196855798 N/A Y

LAIPMansfield 2-78 - No. 2 Power Boiler Total Dioxin/Furans (TEQ) 2 0 0.014761 N/A -4.215766703 N/A Y

LAIPMansfield 2-78 - No. 2 Power Boiler Total Dioxin/Furans (TEQ) 3 0 0.0054579 N/A -5.210691171 N/A Y

TXInternationalPaperQueenCityPB02 Total Dioxin/Furans (TEQ) TXInternationalPaperQueenCity-02-DFT1R1 0 0.000391 N/A -7.846802998 N/A Y

TXInternationalPaperQueenCityPB02 Total Dioxin/Furans (TEQ) TXInternationalPaperQueenCity-02-DFT1R2 0 0.000284 N/A -8.16653632 N/A Y

TXInternationalPaperQueenCityPB02 Total Dioxin/Furans (TEQ) TXInternationalPaperQueenCity-02-DFT1R3 0 0.000829 N/A -7.095290403 N/A Y

WALongviewFPP #20 Power Boiler Total Dioxin/Furans (TEQ) 1 0 0.01324541 N/A -4.324104192 N/A N

WALongviewFPP #20 Power Boiler Total Dioxin/Furans (TEQ) 2 0 0.01910585 N/A -3.957760698 N/A N

WALongviewFPP #20 Power Boiler Total Dioxin/Furans (TEQ) 3 0 0.01339035 N/A -4.31322097 N/A N

Sample Size 9 9

Non-detects 0 0

Average 0.00917 -5.48

Median 0.01325 -4.32

Standard Deviation 0.00740 1.72

Minimum 0.00028 -8.17

Maximum 0.01911 -3.96

Skewness -0.20 -0.82

SE Skewness 0.82 0.82

Skewness Test Normal Normal

Kurtosis -1.92 -1.40

SE Kurtosis 1.63 1.63

Kurtosis Test Normal Normal

99.0% t-statistic for UL 2.82 2.82

99.0% UL 0.0301 0.54

99.0% t-statistic for UPL 2.90 2.90

99.0% UPL 0.0235 0.1161

95.0% t-statistic for UL 1.83 1.83

95.0% UL 0.0227 0.0981

95.0% t-statistic for UPL 1.86 1.86

95.0% UPL 0.0183 0.0353

Maximum TEQ DL less than average: N/A

3x Max TEQ DL less than average: N/A

Page 1
Facility ID Combustion Unit ID Run ID Test ID Pollutant

LAIPMansfield 2-78 - No. 2 Power Boiler 1,2,3,4,6,5,7,8 OCDD-8/1998 LAIPMansfieldDF-OCDD12346578-T1R1 1,2,3,4,6,7,8,9 OCDD

LAIPMansfield 2-78 - No. 2 Power Boiler 1,2,3,4,6,5,7,8 OCDF-8/1998 LAIPMansfieldDF-OCDF12346578-T1R1 1,2,3,4,6,7,8,9 OCDF

LAIPMansfield 2-78 - No. 2 Power Boiler 1,2,3,4,6,7,8 HpCDD-8/1998 LAIPMansfieldDF-HpCDD1234678-T1R1 1,2,3,4,6,7,8 HpCDD

LAIPMansfield 2-78 - No. 2 Power Boiler 1,2,3,4,6,7,8 HpCDF-8/1998 LAIPMansfieldDF-HpCDF1234678-T1R1 1,2,3,4,6,7,8 HpCDF

LAIPMansfield 2-78 - No. 2 Power Boiler 1,2,3,4,7,8,9 HpCDF-8/1998 LAIPMansfieldDF-HpCDF1234789-T1R1 1,2,3,4,7,8,9 HpCDF

LAIPMansfield 2-78 - No. 2 Power Boiler 1,2,3,6,7,8 HxCDD-8/1998 LAIPMansfieldDF-HxCDD123478-T1R1 1,2,3,6,7,8 HxCDD

LAIPMansfield 2-78 - No. 2 Power Boiler 1,2,3,6,7,8 HxCDD-8/1998 LAIPMansfieldDF-HxCDD123678-T1R1 1,2,3,6,7,8 HxCDD

LAIPMansfield 2-78 - No. 2 Power Boiler 1,2,3,6,7,8 HxCDF-8/1998 LAIPMansfieldDF-HxCDF123678-T1R1 1,2,3,6,7,8 HxCDF

LAIPMansfield 2-78 - No. 2 Power Boiler 1,2,3,6,7,8 HxCDF-8/1998 LAIPMansfieldDF-HxCDF123478-T1R1 1,2,3,6,7,8 HxCDF

LAIPMansfield 2-78 - No. 2 Power Boiler 1,2,3,7,8 PeCDD-8/1998 LAIPMansfieldDF-PeCDD12378-T1R1 1,2,3,7,8 PeCDD

LAIPMansfield 2-78 - No. 2 Power Boiler 1,2,3,7,8 PeCDF-8/1998 LAIPMansfieldDF-PeCDF12378-T1R1 1,2,3,7,8 PeCDF

LAIPMansfield 2-78 - No. 2 Power Boiler 1,2,3,7,8,9 HxCDD-8/1998 LAIPMansfieldDF-HxCDD123789-T1R1 1,2,3,7,8,9 HxCDD

LAIPMansfield 2-78 - No. 2 Power Boiler 1,2,3,7,8,9 HxCDF-8/1998 LAIPMansfieldDF-HxCDF123789-T1R1 1,2,3,7,8,9 HxCDF

LAIPMansfield 2-78 - No. 2 Power Boiler 16-PAH-8/1998 LAIPMansfield2-16PAH-T1R1 16-PAH

LAIPMansfield 2-78 - No. 2 Power Boiler 2,3,4,6,7,8 HxCDF-8/1998 LAIPMansfieldDF-HxCDF234678-T1R1 2,3,4,6,7,8 HxCDF

LAIPMansfield 2-78 - No. 2 Power Boiler 2,3,4,7,8 PeCDF-8/1998 LAIPMansfieldDF-PeCDF23478-T1R1 2,3,4,7,8 PeCDF

LAIPMansfield 2-78 - No. 2 Power Boiler 2,3,7,8 TCDD-8/1998 LAIPMansfieldDF-TCDD2378-T1R1 2,3,7,8 TCDD

LAIPMansfield 2-78 - No. 2 Power Boiler 2,3,7,8 TCDF-8/1998 LAIPMansfieldDF-TCDFtotal-T1R1 2,3,7,8 TCDF

LAIPMansfield 2-78 - No. 2 Power Boiler 7-PAH-8/1998 LAIPMansfield2-7PAH-T1R1 7-PAH

LAIPMansfield 2-78 - No. 2 Power Boiler Other HpCDD-8/1998 LAIPMansfieldDF-HpCDDtotal-T1R1 Other HpCDD

LAIPMansfield 2-78 - No. 2 Power Boiler Other HpCDF-8/1998 LAIPMansfieldDF-HpCDFtotal-T1R1 Other HpCDF

LAIPMansfield 2-78 - No. 2 Power Boiler Other HxCDD-8/1998 LAIPMansfieldDF-HxCDDtotal-T1R1 Other HxCDD

LAIPMansfield 2-78 - No. 2 Power Boiler Other HxCDF-8/1998 LAIPMansfieldDF-HxCDFtotal-T1R1 Other HxCDF

LAIPMansfield 2-78 - No. 2 Power Boiler Other PCDF-8/1998 LAIPMansfieldDF-PCDFtotal-T1R1 Other PCDF

LAIPMansfield 2-78 - No. 2 Power Boiler Other PeCDD-8/1998 LAIPMansfieldDF-PeCDDtotal-T1R1 Other PeCDD

LAIPMansfield 2-78 - No. 2 Power Boiler Other PeCDF-8/1998 LAIPMansfieldDF-PeCDFtotal-T1R1 Other PeCDF

LAIPMansfield 2-78 - No. 2 Power Boiler Other TCDF-8/1998 LAIPMansfieldDF-TCDFtotal-T1R1 Other TCDF

LAIPMansfield 2-78 - No. 2 Power Boiler Total Dioxin/Furans-8/1998 LAIPMansfield2DFT1R1 Total Dioxin/Furans

TNTempleInland2426 5000F 1,2,3,4,6,7,8 HpCDD-7/2009-BL 2 1,2,3,4,6,7,8 HpCDD

TNTempleInland2426 5000F 1,2,3,4,6,7,8 HpCDF-7/2009-BL 2 1,2,3,4,6,7,8 HpCDF

TNTempleInland2426 5000F 1,2,3,4,6,5,7,8 OCDD-7/2009-BL 2 1,2,3,4,6,7,8,9 OCDD

TNTempleInland2426 5000F 1,2,3,4,6,5,7,8 OCDF-7/2009-BL 2 1,2,3,4,6,7,8,9 OCDF

TNTempleInland2426 5000F 1,2,3,4,7,8 HxCDD-7/2009-BL 2 1,2,3,4,7,8 HxCDD

TNTempleInland2426 5000F 1,2,3,4,7,8 HxCDF-7/2009-BL 2 1,2,3,4,7,8 HxCDF

TNTempleInland2426 5000F 1,2,3,4,7,8,9 HpCDF-7/2009-BL 2 1,2,3,4,7,8,9 HpCDF

TNTempleInland2426 5000F 1,2,3,6,7,8 HxCDD-7/2009-BL 2 1,2,3,6,7,8 HxCDD

TNTempleInland2426 5000F 1,2,3,6,7,8 HxCDF-7/2009-BL 2 1,2,3,6,7,8 HxCDF

TNTempleInland2426 5000F 1,2,3,7,8 PeCDD-7/2009-BL 2 1,2,3,7,8 PeCDD

TNTempleInland2426 5000F 1,2,3,7,8 PeCDF-7/2009-BL 2 1,2,3,7,8 PeCDF

TNTempleInland2426 5000F 1,2,3,7,8,9 HxCDD-7/2009-BL 2 1,2,3,7,8,9 HxCDD

TNTempleInland2426 5000F 1,2,3,7,8,9 HxCDF-7/2009-BL 2 1,2,3,7,8,9 HxCDF

TNTempleInland2426 5000F 2,3,4,6,7,8 HxCDF-7/2009-BL 2 2,3,4,6,7,8 HxCDF

TNTempleInland2426 5000F 2,3,4,7,8 PeCDF-7/2009-BL 2 2,3,4,7,8 PeCDF

TNTempleInland2426 5000F 2,3,7,8 TCDD-7/2009-BL 2 2,3,7,8 TCDD

TNTempleInland2426 5000F 2,3,7,8 TCDF-7/2009-BL 2 2,3,7,8 TCDF

TNTempleInland2426 5000F Other HpCDD-7/2009-BL 2 Other HpCDD

TNTempleInland2426 5000F Other HpCDF-7/2009-BL 2 Other HpCDF

TNTempleInland2426 5000F Other HxCDD-7/2009-BL 2 Other HxCDD

TNTempleInland2426 5000F Other HxCDF-7/2009-BL 2 Other HxCDF

TNTempleInland2426 5000F Other PeCDD-7/2009-BL 2 Other PeCDD
TNTempleInland2426 5000F Other PeCDF-7/2009-BL 2 Other PeCDF

TNTempleInland2426 5000F Other TCDD-7/2009-BL 2 Other TCDD

TNTempleInland2426 5000F Other TCDF-7/2009-BL-1 2 Other TCDF

TNTempleInland2426 5000F Total Dioxin/Furans-7/2009-BL 2 Total Dioxin/Furans

TNTempleInland2426 5000F 1,2,3,4,6,7,8 HpCDD-7/2009-BL 3 1,2,3,4,6,7,8 HpCDD

TNTempleInland2426 5000F 1,2,3,4,6,7,8 HpCDF-7/2009-BL 3 1,2,3,4,6,7,8 HpCDF

TNTempleInland2426 5000F 1,2,3,4,6,5,7,8 OCDD-7/2009-BL 3 1,2,3,4,6,7,8,9 OCDD

TNTempleInland2426 5000F 1,2,3,4,6,5,7,8 OCDF-7/2009-BL 3 1,2,3,4,6,7,8,9 OCDF

TNTempleInland2426 5000F 1,2,3,4,7,8 HxCDD-7/2009-BL 3 1,2,3,4,7,8 HxCDD

TNTempleInland2426 5000F 1,2,3,4,7,8 HxCDF-7/2009-BL 3 1,2,3,4,7,8 HxCDF

TNTempleInland2426 5000F 1,2,3,4,7,8,9 HpCDF-7/2009-BL 3 1,2,3,4,7,8,9 HpCDF

TNTempleInland2426 5000F 1,2,3,6,7,8 HxCDD-7/2009-BL 3 1,2,3,6,7,8 HxCDD

TNTempleInland2426 5000F 1,2,3,6,7,8 HxCDF-7/2009-BL 3 1,2,3,6,7,8 HxCDF

TNTempleInland2426 5000F 1,2,3,7,8 PeCDD-7/2009-BL 3 1,2,3,7,8 PeCDD

TNTempleInland2426 5000F 1,2,3,7,8 PeCDF-7/2009-BL 3 1,2,3,7,8 PeCDF

TNTempleInland2426 5000F 1,2,3,7,8,9 HxCDD-7/2009-BL 3 1,2,3,7,8,9 HxCDD

TNTempleInland2426 5000F 1,2,3,7,8,9 HxCDF-7/2009-BL 3 1,2,3,7,8,9 HxCDF

TNTempleInland2426 5000F 2,3,4,6,7,8 HxCDF-7/2009-BL 3 2,3,4,6,7,8 HxCDF

TNTempleInland2426 5000F 2,3,4,7,8 PeCDF-7/2009-BL 3 2,3,4,7,8 PeCDF

TNTempleInland2426 5000F 2,3,7,8 TCDD-7/2009-BL 3 2,3,7,8 TCDD

TNTempleInland2426 5000F 2,3,7,8 TCDF-7/2009-BL 3 2,3,7,8 TCDF

TNTempleInland2426 5000F Other HpCDD-7/2009-BL 3 Other HpCDD

TNTempleInland2426 5000F Other HpCDF-7/2009-BL 3 Other HpCDF

TNTempleInland2426 5000F Other HxCDD-7/2009-BL 3 Other HxCDD

TNTempleInland2426 5000F Other HxCDF-7/2009-BL 3 Other HxCDF

TNTempleInland2426 5000F Other PeCDD-7/2009-BL 3 Other PeCDD

TNTempleInland2426 5000F Other PeCDF-7/2009-BL 3 Other PeCDF

TNTempleInland2426 5000F Other TCDD-7/2009-BL 3 Other TCDD

TNTempleInland2426 5000F Other TCDF-7/2009-BL-1 3 Other TCDF

TNTempleInland2426 5000F Total Dioxin/Furans-7/2009-BL 3 Total Dioxin/Furans

TNTempleInland2426 5000F 1,2,3,4,6,7,8 HpCDD-7/2009-B 1 1,2,3,4,6,7,8 HpCDD

TNTempleInland2426 5000F 1,2,3,4,6,7,8 HpCDF-7/2009-B 1 1,2,3,4,6,7,8 HpCDF

TNTempleInland2426 5000F 1,2,3,4,6,5,7,8 OCDD-7/2009-B 1 1,2,3,4,6,7,8,9 OCDD

TNTempleInland2426 5000F 1,2,3,4,6,5,7,8 OCDF-7/2009-B 1 1,2,3,4,6,7,8,9 OCDF

TNTempleInland2426 5000F 1,2,3,4,7,8 HxCDD-7/2009-B 1 1,2,3,4,7,8 HxCDD

TNTempleInland2426 5000F 1,2,3,4,7,8 HxCDF-7/2009-B 1 1,2,3,4,7,8 HxCDF

TNTempleInland2426 5000F 1,2,3,4,7,8,9 HpCDF-7/2009-B 1 1,2,3,4,7,8,9 HpCDF

TNTempleInland2426 5000F 1,2,3,6,7,8 HxCDD-7/2009-B 1 1,2,3,6,7,8 HxCDD

TNTempleInland2426 5000F 1,2,3,6,7,8 HxCDF-7/2009-B 1 1,2,3,6,7,8 HxCDF

TNTempleInland2426 5000F 1,2,3,7,8 PeCDD-7/2009-B 1 1,2,3,7,8 PeCDD

TNTempleInland2426 5000F 1,2,3,7,8 PeCDF-7/2009-B 1 1,2,3,7,8 PeCDF

TNTempleInland2426 5000F 1,2,3,7,8,9 HxCDD-7/2009-B 1 1,2,3,7,8,9 HxCDD

TNTempleInland2426 5000F 1,2,3,7,8,9 HxCDF-7/2009-B 1 1,2,3,7,8,9 HxCDF

TNTempleInland2426 5000F 2,3,4,6,7,8 HxCDF-7/2009-B 1 2,3,4,6,7,8 HxCDF

TNTempleInland2426 5000F 2,3,4,7,8 PeCDF-7/2009-B 1 2,3,4,7,8 PeCDF

TNTempleInland2426 5000F 2,3,7,8 TCDD-7/2009-B 1 2,3,7,8 TCDD

TNTempleInland2426 5000F 2,3,7,8 TCDF-7/2009-B 1 2,3,7,8 TCDF

TNTempleInland2426 5000F Other HpCDD-7/2009-B 1 Other HpCDD

TNTempleInland2426 5000F Other HpCDF-7/2009-B 1 Other HpCDF

TNTempleInland2426 5000F Other HxCDD-7/2009-B 1 Other HxCDD
TNTempleInland2426 5000F Other HxCDF-7/2009-B 1 Other HxCDF

TNTempleInland2426 5000F Other PeCDD-7/2009-B 1 Other PeCDD

TNTempleInland2426 5000F Other PeCDF-7/2009-B 1 Other PeCDF

TNTempleInland2426 5000F Other TCDD-7/2009-B 1 Other TCDD

TNTempleInland2426 5000F Other TCDF-7/2009-B-1 1 Other TCDF

TNTempleInland2426 5000F Total Dioxin/Furans-7/2009-B 1 Total Dioxin/Furans

TNTempleInland2426 5000F 1,2,3,4,6,7,8 HpCDD-7/2009-B 2 1,2,3,4,6,7,8 HpCDD

TNTempleInland2426 5000F 1,2,3,4,6,7,8 HpCDF-7/2009-B 2 1,2,3,4,6,7,8 HpCDF

TNTempleInland2426 5000F 1,2,3,4,6,5,7,8 OCDD-7/2009-B 2 1,2,3,4,6,7,8,9 OCDD

TNTempleInland2426 5000F 1,2,3,4,6,5,7,8 OCDF-7/2009-B 2 1,2,3,4,6,7,8,9 OCDF

TNTempleInland2426 5000F 1,2,3,4,7,8 HxCDD-7/2009-B 2 1,2,3,4,7,8 HxCDD

TNTempleInland2426 5000F 1,2,3,4,7,8 HxCDF-7/2009-B 2 1,2,3,4,7,8 HxCDF

TNTempleInland2426 5000F 1,2,3,4,7,8,9 HpCDF-7/2009-B 2 1,2,3,4,7,8,9 HpCDF

TNTempleInland2426 5000F 1,2,3,6,7,8 HxCDD-7/2009-B 2 1,2,3,6,7,8 HxCDD

TNTempleInland2426 5000F 1,2,3,6,7,8 HxCDF-7/2009-B 2 1,2,3,6,7,8 HxCDF

TNTempleInland2426 5000F 1,2,3,7,8 PeCDD-7/2009-B 2 1,2,3,7,8 PeCDD

TNTempleInland2426 5000F 1,2,3,7,8 PeCDF-7/2009-B 2 1,2,3,7,8 PeCDF

TNTempleInland2426 5000F 1,2,3,7,8,9 HxCDD-7/2009-B 2 1,2,3,7,8,9 HxCDD

TNTempleInland2426 5000F 1,2,3,7,8,9 HxCDF-7/2009-B 2 1,2,3,7,8,9 HxCDF

TNTempleInland2426 5000F 2,3,4,6,7,8 HxCDF-7/2009-B 2 2,3,4,6,7,8 HxCDF

TNTempleInland2426 5000F 2,3,4,7,8 PeCDF-7/2009-B 2 2,3,4,7,8 PeCDF

TNTempleInland2426 5000F 2,3,7,8 TCDD-7/2009-B 2 2,3,7,8 TCDD

TNTempleInland2426 5000F 2,3,7,8 TCDF-7/2009-B 2 2,3,7,8 TCDF

TNTempleInland2426 5000F Other HpCDD-7/2009-B 2 Other HpCDD

TNTempleInland2426 5000F Other HpCDF-7/2009-B 2 Other HpCDF

TNTempleInland2426 5000F Other HxCDD-7/2009-B 2 Other HxCDD

TNTempleInland2426 5000F Other HxCDF-7/2009-B 2 Other HxCDF

TNTempleInland2426 5000F Other PeCDD-7/2009-B 2 Other PeCDD

TNTempleInland2426 5000F Other PeCDF-7/2009-B 2 Other PeCDF

TNTempleInland2426 5000F Other TCDD-7/2009-B 2 Other TCDD

TNTempleInland2426 5000F Other TCDF-7/2009-B-1 2 Other TCDF

TNTempleInland2426 5000F Total Dioxin/Furans-7/2009-B 2 Total Dioxin/Furans

TNTempleInland2426 5000F 1,2,3,4,6,7,8 HpCDD-7/2009-B 3 1,2,3,4,6,7,8 HpCDD

TNTempleInland2426 5000F 1,2,3,4,6,7,8 HpCDF-7/2009-B 3 1,2,3,4,6,7,8 HpCDF

TNTempleInland2426 5000F 1,2,3,4,6,5,7,8 OCDD-7/2009-B 3 1,2,3,4,6,7,8,9 OCDD

TNTempleInland2426 5000F 1,2,3,4,6,5,7,8 OCDF-7/2009-B 3 1,2,3,4,6,7,8,9 OCDF

TNTempleInland2426 5000F 1,2,3,4,7,8 HxCDD-7/2009-B 3 1,2,3,4,7,8 HxCDD

TNTempleInland2426 5000F 1,2,3,4,7,8 HxCDF-7/2009-B 3 1,2,3,4,7,8 HxCDF

TNTempleInland2426 5000F 1,2,3,4,7,8,9 HpCDF-7/2009-B 3 1,2,3,4,7,8,9 HpCDF

TNTempleInland2426 5000F 1,2,3,6,7,8 HxCDD-7/2009-B 3 1,2,3,6,7,8 HxCDD

TNTempleInland2426 5000F 1,2,3,6,7,8 HxCDF-7/2009-B 3 1,2,3,6,7,8 HxCDF

TNTempleInland2426 5000F 1,2,3,7,8 PeCDD-7/2009-B 3 1,2,3,7,8 PeCDD

TNTempleInland2426 5000F 1,2,3,7,8 PeCDF-7/2009-B 3 1,2,3,7,8 PeCDF

TNTempleInland2426 5000F 1,2,3,7,8,9 HxCDD-7/2009-B 3 1,2,3,7,8,9 HxCDD

TNTempleInland2426 5000F 1,2,3,7,8,9 HxCDF-7/2009-B 3 1,2,3,7,8,9 HxCDF

TNTempleInland2426 5000F 2,3,4,6,7,8 HxCDF-7/2009-B 3 2,3,4,6,7,8 HxCDF

TNTempleInland2426 5000F 2,3,4,7,8 PeCDF-7/2009-B 3 2,3,4,7,8 PeCDF

TNTempleInland2426 5000F 2,3,7,8 TCDD-7/2009-B 3 2,3,7,8 TCDD

TNTempleInland2426 5000F 2,3,7,8 TCDF-7/2009-B 3 2,3,7,8 TCDF

TNTempleInland2426 5000F Other HpCDD-7/2009-B 3 Other HpCDD
TNTempleInland2426 5000F Other HpCDF-7/2009-B

3 Other HpCDF

TNTempleInland2426 5000F Other HxCDD-7/2009-B3 Other HxCDD

TNTempleInland2426 5000F Other HxCDF-7/2009-B3 Other HxCDF

TNTempleInland2426 5000F Other PeCDD-7/2009-B3 Other PeCDD

TNTempleInland2426 5000F Other PeCDF-7/2009-B3 Other PeCDF

TNTempleInland2426 5000F Other TCDD-7/2009-B3 Other TCDD

TNTempleInland2426 5000F Other TCDF-7/2009-B-13 Other TCDF

TNTempleInland2426 5000F Total Dioxin/Furans-7/2009-B3 Total Dioxin/Furans
Dates Tested Non Detect? ND Count Emissions Normalized Normalized Units (7%O2) TEFvalue_05

26-Aug-98 0 0.259 ng/dscm @ 7% O2 0.01

26-Aug-98 0 0.417 ng/dscm @ 7% O2 0.01

26-Aug-98 0 0.035 ng/dscm @ 7% O2 0.0003

26-Aug-98 0 0.131 ng/dscm @ 7% O2 0.0003

26-Aug-98 0 0.026 ng/dscm @ 7% O2 0.1

26-Aug-98 0 0.002 ng/dscm @ 7% O2 0.1

26-Aug-98 0 0.004 ng/dscm @ 7% O2 0.01

26-Aug-98 0 0.011 ng/dscm @ 7% O2 0.1

26-Aug-98 0 0.012 ng/dscm @ 7% O2 0.1

26-Aug-98 0 0.001 ng/dscm @ 7% O2 1

26-Aug-98 0 0.004 ng/dscm @ 7% O2 0.03

26-Aug-98 0 0.004 ng/dscm @ 7% O2 0.1

26-Aug-98 0 0.009 ng/dscm @ 7% O2

25-Aug-98 0 0.002462857 mg/dscm @ 7% O2

26-Aug-98 0 0.028 ng/dscm @ 7% O2 0.1

26-Aug-98 0 0.006 ng/dscm @ 7% O2 0.1

26-Aug-98 0 0 ng/dscm @ 7% O2 0.3

26-Aug-98 0 0.003 ng/dscm @ 7% O2 1

25-Aug-98 ND 1 1

26-Aug-98 0 0.07 ng/dscm @ 7% O2 0

26-Aug-98 0 0.24 ng/dscm @ 7% O2 0

26-Aug-98 0 0.058 ng/dscm @ 7% O2 0

26-Aug-98 0 0.134 ng/dscm @ 7% O2 0

26-Aug-98 0 0.064 ng/dscm @ 7% O2 0

26-Aug-98 0 0.022 ng/dscm @ 7% O2 0

26-Aug-98 0 0.067 ng/dscm @ 7% O2 0

26-Aug-98 0 0.064 ng/dscm @ 7% O2 0

25-Aug-98 0 1.671 ng/dscm @ 7% O2

ND Count Emissions Normalized

10-Jul-09 0 0.01 ng/dscm @ 7% O2 0.01

10-Jul-09 ND 1 0.022 ng/dscm @ 7% O2 0.01

10-Jul-09 0 0.033 ng/dscm @ 7% O2 0.0003

10-Jul-09 0 0.013 ng/dscm @ 7% O2 0.0003

10-Jul-09 0 0.0014 ng/dscm @ 7% O2 0.1

10-Jul-09 0 0.01 ng/dscm @ 7% O2 0.1

10-Jul-09 ND 1 0.0028 ng/dscm @ 7% O2 0.01

10-Jul-09 0 0.0024 ng/dscm @ 7% O2 0.1

10-Jul-09 0 0.0082 ng/dscm @ 7% O2 0.1

10-Jul-09 0 0.0017 ng/dscm @ 7% O2 1

10-Jul-09 0 0.0075 ng/dscm @ 7% O2 0.03

10-Jul-09 0 0.0018 ng/dscm @ 7% O2 0.1

10-Jul-09 0 0.0062 ng/dscm @ 7% O2 0.1

10-Jul-09 0 0.0007 ng/dscm @ 7% O2 0.1

10-Jul-09 0 0.014 ng/dscm @ 7% O2 0.3

10-Jul-09 ND 1 0.0011 ng/dscm @ 7% O2 1

10-Jul-09 0 0.01 ng/dscm @ 7% O2 1

10-Jul-09 0 0.02 ng/dscm @ 7% O2 0

10-Jul-09 0 0.0052 ng/dscm @ 7% O2 0

10-Jul-09 0 0.037 ng/dscm @ 7% O2 0

10-Jul-09 0 0.081 ng/dscm @ 7% O2 0

10-Jul-09 0 0.02 ng/dscm @ 7% O2 0
10-Jul-09

0 0.17 ng/dscm @ 7% O20

10-Jul-090 0.037 ng/dscm @ 7% O20

10-Jul-090 0.33 ng/dscm @ 7% O20

10-Jul-09 ND1 0.82 ng/dscm @ 7% O2

ND Count Emissions Normalized

10-Jul-090 0.0078 ng/dscm @ 7% O2 0.01

10-Jul-09 ND1 0.012 ng/dscm @ 7% O2 0.01

10-Jul-090 0.023 ng/dscm @ 7% O2 0.0003

10-Jul-090 0.0087 ng/dscm @ 7% O2 0.0003

10-Jul-090 0.0009 ng/dscm @ 7% O2 0.1

10-Jul-090 0.0043 ng/dscm @ 7% O2 0.1

10-Jul-09 ND1 0.0019 ng/dscm @ 7% O2 0.01

10-Jul-090 0.0015 ng/dscm @ 7% O2 0.1

10-Jul-090 0.0036 ng/dscm @ 7% O2 0.1

10-Jul-09 ND1 0.001 ng/dscm @ 7% O21

10-Jul-090 0.0031 ng/dscm @ 7% O2 0.03

10-Jul-090 0.0012 ng/dscm @ 7% O2 0.1

10-Jul-09 ND1 0.003 ng/dscm @ 7% O2 0.1

10-Jul-090 0.00037 ng/dscm @ 7% O2 0.1

10-Jul-090 0.0051 ng/dscm @ 7% O2 0.3

10-Jul-09 ND1 0.00057 ng/dscm @ 7% O21

10-Jul-090 0.0033 ng/dscm @ 7% O21

10-Jul-090 0.015 ng/dscm @ 7% O20

10-Jul-090 0.0032 ng/dscm @ 7% O20

10-Jul-090 0.024 ng/dscm @ 7% O20

10-Jul-090 0.034 ng/dscm @ 7% O20

10-Jul-090 0.012 ng/dscm @ 7% O20

10-Jul-090 0.059 ng/dscm @ 7% O20

10-Jul-090 0.022 ng/dscm @ 7% O20

10-Jul-090 0.11 ng/dscm @ 7% O20

10-Jul-09 ND1 0.34 ng/dscm @ 7% O2

ND Count Emissions Normalized

07-Jul-090 0.014 ng/dscm @ 7% O2 0.01

07-Jul-09 ND1 0.039 ng/dscm @ 7% O2 0.01

07-Jul-090 0.034 ng/dscm @ 7% O2 0.0003

07-Jul-090 0.028 ng/dscm @ 7% O2 0.0003

07-Jul-090 0.0017 ng/dscm @ 7% O2 0.1

07-Jul-090 0.013 ng/dscm @ 7% O2 0.1

07-Jul-090 0.0065 ng/dscm @ 7% O2 0.01

07-Jul-090 0.0028 ng/dscm @ 7% O2 0.1

07-Jul-090 0.01 ng/dscm @ 7% O2 0.1

07-Jul-090 0.0017 ng/dscm @ 7% O21

07-Jul-090 0.0075 ng/dscm @ 7% O2 0.03

07-Jul-090 0.0015 ng/dscm @ 7% O2 0.1

07-Jul-090 0.0078 ng/dscm @ 7% O2 0.1

07-Jul-090 0.0014 ng/dscm @ 7% O2 0.1

07-Jul-090 0.013 ng/dscm @ 7% O2 0.3

07-Jul-09 ND1 0.001 ng/dscm @ 7% O21

07-Jul-090 0.0099 ng/dscm @ 7% O21

07-Jul-090 0.028 ng/dscm @ 7% O20

07-Jul-090 0.023 ng/dscm @ 7% O20

07-Jul-090 0.047 ng/dscm @ 7% O20
07-Jul-09

0 0.096 ng/dscm @ 7% O20

07-Jul-090 0.021 ng/dscm @ 7% O20

07-Jul-090 0.13 ng/dscm @ 7% O20

07-Jul-090 0.035 ng/dscm @ 7% O20

07-Jul-090 0.28 ng/dscm @ 7% O20

07-Jul-09 ND1 0.86 ng/dscm @ 7% O2

ND Count Emissions Normalized

07-Jul-090 0.0063 ng/dscm @ 7% O2 0.01

07-Jul-09 ND1 0.01 ng/dscm @ 7% O2 0.01

07-Jul-090 0.017 ng/dscm @ 7% O2 0.0003

07-Jul-090 0.0057 ng/dscm @ 7% O2 0.0003

07-Jul-090 0.00088 ng/dscm @ 7% O2 0.1

07-Jul-090 0.0043 ng/dscm @ 7% O2 0.1

07-Jul-090 0.0015 ng/dscm @ 7% O2 0.01

07-Jul-090 0.0014 ng/dscm @ 7% O2 0.1

07-Jul-090 0.004 ng/dscm @ 7% O2 0.1

07-Jul-090 0.0014 ng/dscm @ 7% O21

07-Jul-090 0.0072 ng/dscm @ 7% O2 0.03

07-Jul-090 0.0012 ng/dscm @ 7% O2 0.1

07-Jul-09 ND1 0.0031 ng/dscm @ 7% O2 0.1

07-Jul-090 0.00043 ng/dscm @ 7% O2 0.1

07-Jul-090 0.0095 ng/dscm @ 7% O2 0.3

07-Jul-09 ND1 0.0012 ng/dscm @ 7% O21

07-Jul-090 0.013 ng/dscm @ 7% O21

07-Jul-090 0.012 ng/dscm @ 7% O20

07-Jul-090 0.0036 ng/dscm @ 7% O20

07-Jul-090 0.02 ng/dscm @ 7% O20

07-Jul-090 0.038 ng/dscm @ 7% O20

07-Jul-090 0.014 ng/dscm @ 7% O20

07-Jul-090 0.12 ng/dscm @ 7% O20

07-Jul-090 0.027 ng/dscm @ 7% O20

07-Jul-090 0.44 ng/dscm @ 7% O20

07-Jul-09 ND1 0.77 ng/dscm @ 7% O2

ND Count Emissions Normalized

08-Jul-090 0.016 ng/dscm @ 7% O2 0.01

08-Jul-09 ND1 0.025 ng/dscm @ 7% O2 0.01

08-Jul-090 0.034 ng/dscm @ 7% O2 0.0003

08-Jul-090 0.014 ng/dscm @ 7% O2 0.0003

08-Jul-090 0.0017 ng/dscm @ 7% O2 0.1

08-Jul-090 0.0091 ng/dscm @ 7% O2 0.1

08-Jul-090 0.0034 ng/dscm @ 7% O2 0.01

08-Jul-090 0.0031 ng/dscm @ 7% O2 0.1

08-Jul-090 0.007 ng/dscm @ 7% O2 0.1

08-Jul-090 0.0022 ng/dscm @ 7% O21

08-Jul-090 0.006 ng/dscm @ 7% O2 0.03

08-Jul-090 0.0022 ng/dscm @ 7% O2 0.1

08-Jul-090 0.0062 ng/dscm @ 7% O2 0.1

08-Jul-090 0.00061 ng/dscm @ 7% O2 0.1

08-Jul-090 0.011 ng/dscm @ 7% O2 0.3

08-Jul-09 ND1 0.0011 ng/dscm @ 7% O21

08-Jul-090 0.0089 ng/dscm @ 7% O21

08-Jul-090 0.033 ng/dscm @ 7% O20
08-Jul-09

0 0.014 ng/dscm @ 7% O20

08-Jul-090 0.051 ng/dscm @ 7% O20

08-Jul-090 0.067 ng/dscm @ 7% O20

08-Jul-090 0.025 ng/dscm @ 7% O20

08-Jul-090 0.12 ng/dscm @ 7% O20

08-Jul-090 0.039 ng/dscm @ 7% O20

08-Jul-090 0.26 ng/dscm @ 7% O20

08-Jul-09 ND1 0.75 ng/dscm @ 7% O2

ND Count1
DL Average Run (TMB)DL TEQ Average Run (ND use average, ADL use reported) DL TEQ Average Run

0.00259 #DIV/0!

#DIV/0! #DIV/0!

0.0000105 #DIV/0!

0.0000393 #DIV/0!

0.0026 #DIV/0!

0.0002 #DIV/0!

#DIV/0! #DIV/0!

0.0011 #DIV/0!

0.0012 #DIV/0!

0.001 #DIV/0!

0.00012 #DIV/0!

0.0004 #DIV/0!

0.0028 #DIV/0!

0.0006 #DIV/0!

0 #DIV/0!

#DIV/0! #DIV/0!

0 #DIV/0!

0 #DIV/0!

0 #DIV/0!

0 #DIV/0!

0 #DIV/0!

0 #DIV/0!

0 #DIV/0!

0 #DIV/0!

0 #DIV/0!

#DIV/0! #DIV/0! #DIV/0!

0.0001 8.63333E-05

8.63333E-05 8.63333E-05

0.0000099 0.00000259

0.0000039 0.00000259

0.00014 0.000863333

0.001 0.000863333

8.63333E-05 8.63333E-05

0.00024 0.000863333

0.00082 0.000863333

0.0017 0.008633333

0.000225 0.000259

0.00018 0.000863333

0.00062 0.000863333

0.00007 0.000863333

0.0042 0.00259

0.008633333 0.008633333

0.01 0.008633333

0 0

0 0

0 0

0 0

0 0
0 0

0 0

0 0

0.008633333 0.0281148 0.035056513

0.000078 0.00003694

0.00003694 0.00003694

0.0000069 1.1082E-06

0.00000261 1.1082E-06

0.00009 0.0003694

0.00043 0.0003694

0.00003694 0.00003694

0.00015 0.0003694

0.00036 0.0003694

0.003694 0.003694

0.000093 0.00011082

0.00012 0.0003694

0.0003694 0.0003694

0.000037 0.0003694

0.00153 0.0011082

0.003694 0.003694

0.0033 0.003694

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0.003694 0.01402879 0.014999856

0.00014 0.0002

0.0002 0.0002

0.0000102 0.000006

0.0000084 0.000006

0.00017 0.002

0.0013 0.002

0.000065 0.0002

0.00028 0.002

0.001 0.002

0.0017 0.02

0.000225 0.0006

0.00015 0.002

0.00078 0.002

0.00014 0.002

0.0039 0.006

0.02 0.02

0.0099 0.02

0 0

0 0

0 0
0 0

0 0

0 0

0 0

0 0

0.02 0.0399686 0.081212

0.000063 4.76667E-05

4.76667E-05 4.76667E-05

0.0000051 0.00000143

0.00000171 0.00000143

0.000088 0.000476667

0.00043 0.000476667

0.000015 4.76667E-05

0.00014 0.000476667

0.0004 0.000476667

0.0014 0.004766667

0.000216 0.000143

0.00012 0.000476667

0.000476667 0.000476667

0.000043 0.000476667

0.00285 0.00143

0.004766667 0.004766667

0.013 0.004766667

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0.004766667 0.02406281 0.019355527

0.00016 0.0001305

0.0001305 0.0001305

0.0000102 0.000003915

0.0000042 0.000003915

0.00017 0.001305

0.00091 0.001305

0.000034 0.0001305

0.00031 0.001305

0.0007 0.001305

0.0022 0.01305

0.00018 0.0003915

0.00022 0.001305

0.00062 0.001305

0.000061 0.001305

0.0033 0.003915

0.01305 0.01305

0.0089 0.01305

0 0
0

0

00

00

00

00

00

00

0.01305 0.0309599 0.05299083
EG Variability Summary

ERUs - Biomass

Top 3 Units

Pollutant Type Statistic Normal Ln-transformed

Sample Size 12 12

Non-detects 4 4

Average 0.000167402 -9.016786619

Median 0.000181147 -8.61622435

Standard Deviation 9.63014E-05 1.079446298

Minimum 1.07062E-05 -11.44468407

Maximum 0.000384271 -7.864163422

Skewness 0.357231892 -1.777216913

SE Skewness 0.707106781 0.707106781

Skewness Test Normal Normal

Kurtosis 2.109180987 2.218658911

SE Kurtosis 1.414213562 1.414213562

Kurtosis Test Normal Normal

99.0% t-statistic for UL 2.680997992 2.680997992

99.0% UL 0.000425586 0.002192324

99.0% t-statistic for UPL 2.718079183 2.718079183

99.0% UPL 0.000336364 0.000806437

95.0% t-statistic for UL 1.782287548 1.782287548

95.0% UL 0.000339039 0.000830982

95.0% t-statistic for UPL 1.795884814 1.795884814

95.0% UPL 0.000279039 0.000424138

3x highest DL less than average 0.000442191

Sample Size 15 15

Non-detects 0 0

Average 141.8976288 4.874405614

Median 123.8 4.81866736

Standard Deviation 65.44175613 0.398229908

Minimum 66.1 4.191168747

Maximum 299 5.700443573

Skewness 1.586465841 0.811075025

SE Skewness 0.632455532 0.632455532

Skewness Test Non-normal Normal

Kurtosis 1.822950107 0.684205171

SE Kurtosis 1.264911064 1.264911064

Kurtosis Test Normal Normal

99.0% t-statistic for UL 2.60248029 2.60248029

99.0% UL 312.2085093 368.9979543

99.0% t-statistic for UPL 2.624494064 2.624494064

99.0% UPL 250.5228154 253.5136827

95.0% t-statistic for UL 1.753050325 1.753050325

95.0% UL 256.6203206 263.0969732

95.0% t-statistic for UPL 1.761310115 1.761310115

95.0% UPL 214.7964943 203.9783682

3x highest DL less than average N/A

Sample Size 9 9

Non-detects 1 1

Average 0.099589782 -2.358606065

Cadmium (Cd)

(mg/dscm 

@7%O2)

EG

Carbon 

Monoxide (CO)

(ppmdv@7%O2)

EG
Median 0.099536175 -2.307234133

Standard Deviation 0.031099818 0.362338198

Minimum 0.0425 -3.158251203

Maximum 0.153 -1.877317358

Skewness -0.153706964 -1.279003011

SE Skewness 0.816496581 0.816496581

Skewness Test Normal Normal

Kurtosis 0.993404031 2.747744159

SE Kurtosis 1.632993162 1.632993162

Kurtosis Test Normal Normal

99.0% t-statistic for UL 2.821437921 2.821437921

99.0% UL 0.187335988 0.26281857

99.0% t-statistic for UPL 2.896459446 2.896459446

99.0% UPL 0.15964269 0.190340482

95.0% t-statistic for UL 1.833112923 1.833112923

95.0% UL 0.156599261 0.183709563

95.0% t-statistic for UPL 1.859548033 1.859548033

95.0% UPL 0.138144186 0.148166909

3x highest DL less than average 0.1275

Sample Size 9 9

Non-detects 0 0

Average 0.002128592 -6.518113108

Median 0.00108 -6.830794238

Standard Deviation 0.002509314 0.802812449

Minimum 0.000572247 -7.465939221

Maximum 0.008592729 -4.756838933

Skewness 2.641895853 1.421106554

SE Skewness 0.816496581 0.816496581

Skewness Test Non-normal Normal

Kurtosis 7.314116551 2.300732143

SE Kurtosis 1.632993162 1.632993162

Kurtosis Test Non-normal Normal

99.0% t-statistic for UL 2.821437921 2.821437921

99.0% UL 0.009208466 0.014221113

99.0% t-statistic for UPL 2.896459446 2.896459446

99.0% UPL 0.00697401 0.006957716

95.0% t-statistic for UL 1.833112923 1.833112923

95.0% UL 0.006728448 0.006432016

95.0% t-statistic for UPL 1.859548033 1.859548033

95.0% UPL 0.005239386 0.003994377

3x highest DL less than average N/A

Sample Size 9 9

Non-detects 6 6

Average 0.0002518 -8.826056687

Median 0.000371111 -7.89900843

Standard Deviation 0.000181319 1.380708855

Minimum 1.07062E-05 -11.44468407

Maximum 0.000416 -7.784825298

Skewness -0.437146544 -1.069156639

SE Skewness 0.816496581 0.816496581

Skewness Test Normal Normal

Kurtosis -2.123276325 -0.256988782

Hydrogen 

Chloride 

(HCl)

(ppmdv@7%O2)

EG

Lead (Pb)

(mg/dscm 

@7%O2)

EG

Mercury (Hg)

(mg/dscm EG
SE Kurtosis 1.632993162 1.632993162

Kurtosis Test Normal Normal

99.0% t-statistic for UL 2.821437921 2.821437921

99.0% UL 0.00076338 0.007223091

99.0% t-statistic for UPL 2.896459446 2.896459446

99.0% UPL 0.000601922 0.002112369

95.0% t-statistic for UL 1.833112923 1.833112923

95.0% UL 0.000584178 0.001845396

95.0% t-statistic for UPL 1.859548033 1.859548033

95.0% UPL 0.000476581 0.000813314

3x highest DL less than average 0.000516323

Sample Size 12 12

Non-detects 0 0

Average 86.7594655 4.216531885

Median 109.8217716 4.693031235

Standard Deviation 49.44773336 0.824312884

Minimum 20.68 3.02916705

Maximum 136.08 4.913242948

Skewness -0.55555003 -0.740374056

SE Skewness 0.707106781 0.707106781

Skewness Test Normal Normal

Kurtosis -1.734566436 -1.627674627

SE Kurtosis 1.414213562 1.414213562

Kurtosis Test Normal Normal

99.0% t-statistic for UL 2.680997992 2.680997992

99.0% UL 219.3287393 618.0152119

99.0% t-statistic for UPL 2.718079183 2.718079183

99.0% UPL 173.5161352 287.9535551

95.0% t-statistic for UL 1.782287548 1.782287548

95.0% UL 174.8895449 294.6223814

95.0% t-statistic for UPL 1.795884814 1.795884814

95.0% UPL 144.0811898 176.2859249

3x highest DL less than average N/A

Sample Size 16 16

Non-detects 0 0

Average 5.404254018 1.554132446

Median 3.766872598 1.32578803

Standard Deviation 3.426450882 0.490221085

Minimum 2.99 1.095273387

Maximum 14.2 2.653241965

Skewness 1.975155178 1.303208218

SE Skewness 0.612372436 0.612372436

Skewness Test Non-normal Non-normal

Kurtosis 3.152973392 0.945824514

SE Kurtosis 1.224744871 1.224744871

Kurtosis Test Non-normal Normal

99.0% t-statistic for UL 2.583487179 2.583487179

99.0% UL 14.25644594 16.78712685

99.0% t-statistic for UPL 2.60248029 2.60248029

99.0% UPL 11.01458059 10.55711281

95.0% t-statistic for UL 1.745883669 1.745883669

95.0% UL 11.38643866 11.13397709

Nitrogen Oxides 

(NOx)

(ppmdv@7%O2)

EG

(mg/dscm 

@7%O2)

EG

Particulate Matter 

(PM filterable)

(mg/dscm 

@7%O2)

EG
95.0% t-statistic for UPL 1.753050325 1.753050325

95.0% UPL 9.18341225 8.123939882

3x highest DL less than average N/A

Sample Size 9 9

Non-detects 0 0

Average 2.928479437 0.962468856

Median 2.505 0.918288735

Standard Deviation 1.391371925 0.525688239

Minimum 0.932885906 -0.069472373

Maximum 5.4 1.686398954

Skewness 0.528741111 -0.636570228

SE Skewness 0.816496581 0.816496581

Skewness Test Normal Normal

Kurtosis -0.281646084 0.760378798

SE Kurtosis 1.632993162 1.632993162

Kurtosis Test Normal Normal

99.0% t-statistic for UL 2.821437921 2.821437921

99.0% UL 6.854148951 11.53822674

99.0% t-statistic for UPL 2.896459446 2.896459446

99.0% UPL 5.615181009 7.225082354

95.0% t-statistic for UL 1.833112923 1.833112923

95.0% UL 5.479021294 6.862794769

95.0% t-statistic for UPL 1.859548033 1.859548033

95.0% UPL 4.653361389 5.023685744

3x highest DL less than average N/A

Sample Size 9 9

Non-detects 9 9

Average 0.133351916 -2.220087362

Median 0.08497486 -2.465399831

Standard Deviation 0.113874165 0.608150001

Minimum 0.0608 -2.80016549

Maximum 0.42 -0.867500568

Skewness 2.452510558 1.601964737

SE Skewness 0.816496581 0.816496581

Skewness Test Non-normal Normal

Kurtosis 6.304699491 2.500150652

SE Kurtosis 1.632993162 1.632993162

Kurtosis Test Non-normal Normal

99.0% t-statistic for UL 2.821437921 2.821437921

99.0% UL 0.454640804 0.603970522

99.0% t-statistic for UPL 2.896459446 2.896459446

99.0% UPL 0.35323985 0.351422473

95.0% t-statistic for UL 1.833112923 1.833112923

95.0% UL 0.34209612 0.331118244

95.0% t-statistic for UPL 1.859548033 1.859548033

95.0% UPL 0.274521569 0.230809034

3x highest DL less than average 0.21814794

Sample Size 9 9

Non-detects 0 0

Average 0.009167479 -5.480781028

Median 0.01324541 -4.324104192

Standard Deviation 0.00740164 1.723381286

Dioxins/Furans 

(DF)

(Total Mass 

Basis)

(ng/dscm 

@7%O2)

EG

Sulfur Dioxide 

(SO2)

(ppmdv@7%O2)

EG
Minimum 0.000284 -8.16653632

Maximum 0.01910585 -3.957760698

Skewness -0.200284725 -0.816181934

SE Skewness 0.816496581 0.816496581

Skewness Test Normal Normal

Kurtosis -1.920318556 -1.398962313

SE Kurtosis 1.632993162 1.632993162

Kurtosis Test Normal Normal

99.0% t-statistic for UL 2.821437921 2.821437921

99.0% UL 0.030050748 0.538823233

99.0% t-statistic for UPL 2.896459446 2.896459446

99.0% UPL 0.023459847 0.116137742

95.0% t-statistic for UL 1.833112923 1.833112923

95.0% UL 0.022735522 0.098113675

95.0% t-statistic for UPL 1.859548033 1.859548033

95.0% UPL 0.018343283 0.035284641

3x highest DL less than average N/A

Dioxins/Furans 

(DF)

(Toxic 

Equivalents 

Basis)

(ng/dscm 

@7%O2)

EG