### Instructions for filling in the Emission Test Template
This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate runs or sampling events for each of the requested constituents. This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. yellow are required. All cells that are shaded in green are populated using drop

-down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls (example: 8100_Unit_2_EmisTestMethods.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet
1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet. 2. Please enter the control device configuration.

Emission Data Worksheets

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg Hg+2

### , or if the Ontario

- Hydro Method was used, you would need to enter Hg0

### , HgP, and Hg Volatile Organic HAP and Speciated Semi

-Volatile Organic HAP worksheets allow you to use a drop Constituent field to define as many records as needed to record each HAP that you have results for. General instructions follow for these worksheets:

Boiler Operation Information
1. Please provide the values of all requested parameters for each of test run/sample. 2. Please provide any other supporting information or comments in the Other Supporting Information field.

Fuel Information
1. Please enter what types of fuel are being used in your boiler using the drop

-downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples, then enter an input rate of zero. 2. Please enter the unit of measure using the drop down provided. 3. Please enter the test method used to determine the fuel input rate. 4. Please provide any other information that you feel may be important in the Other Supporting Information field.

Emission Data

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and ppmvd @ 7% O 2 

### (parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please also enter these data.

### This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. Fields shaded in down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet.

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg0 

### and , HgP, and Hg+2 

### . However, both the Speciated Volatile Organic HAP worksheets allow you to use a drop

-down provided in the Constituent field to define as many records as needed to record each HAP that you have results for. General instructions

2. Please provide any other supporting information or comments in the Other Supporting Information field.

downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples,

4. Please provide any other information that you feel may be important in the Other Supporting Information field.

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and

(parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please alsoEIA

Facility Code Facility Name Boiler ID

6288 Healy 1Control Device Configuraton

Listed (by

boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICRListed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICREIA

Facility Code Facility Name Boiler ID

6288 Healy 1

1 5/25/2010 1320 5/25/2010 2 5/26/2010 1200 5/26/2010 3 5/27/2010 900 5/27/2010 Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry) Test Method Used
1830 0.000023 Dry U.S. EPA Method 26A-Mod 1701 0.000031 Dry U.S. EPA Method 26A-Mod 1445 0.000052 Dry U.S. EPA Method 26A-Mod Test End Time Hydrogen Cyanide Emission Test ResultsData Flag (ADL,

BDL, DDL) Test Method

Comments ND 3 hour runs, extra time for pH and leak checks 0.000029 246.2 343.6 13.27 14.2 ND 3 hour runs, extra time for pH and leak checks 0.000039 246 354.3 13.41 14.2 ND 3 hour runs, extra time for pH and leak checks 0.000066 246 350.8 13.24 14.14

Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr) Calculated Emission Rate (lb/mmBtu) Flue Gas Moisture (%) Flue Gas CO 2(%)Fuel Input Rate Fuel Type Units of Measure Measurement

Method 5.7 74856.4 322 49485 subbituminous lb/hour 5.67 77136.6 322 50348 subbituminous lb/hour 5.86 77468.7 321 50926 subbituminous lb/hour Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1 Flue Gas O 2(%)Other Supporting InformationAlaska Source

LLC Testing Golden Valley Electric Association EPA ICR Request May 2010

Run Number 1 2 3
Test/Date/Time M26A HCl/HF 5-25-2010, 1320-1830 5-26-2010,

1200-1701 5-27-2010,

0900-1445 DGM Volume Vm cubic feet 125.919 103.697 101.912 DGM Y Factor Y

- 1.01 1.01 1.01 DGM Average Temperature T m Degrees R 565 566 564 Barometric Pressure P bar Inches Hg 28.91 28.92 28.83 Delta H ΔH Inches W ater 2.09 1.31 1.3 Sam ple Volum e at Standard Conditions (Vmstd) Vmstd Standard Cubic Feet 115.402 94.714 93.121
Total Volume of W ater collected Vlc Milliliters 375 311.5 302 Standard Volum e of W ater

(Vwstd) Vwstd Standard Cubic Feet 17.651 14.662 14.215
Stack Gas Moisture Content Bws - 0.1327 0.1341 0.1324 Pitot Tube Coefficient C p - 0.84 0.84 0.84 Average Pitot differential pressure ΔP Inches W ater 1.09 1.16 1.17 Square Root of Differential Pressure - 1.04 1.08 1.08 Average Stack Gas Temperature

(TsAv) Ts(ave) Degrees R 782 782 781
Measured Stack Pressure P g Inches W ater 2.5 2.5 2.0 Absolute Stack Pressure P s Inches Hg 29.09 29.10 28.98 Stack Oxygen % 5.7 5.67 5.86 Stack CO2 % 14.20 14.20 14.14 Stack %N 2+ %CO % 80.1 80.1 80.0 Stack Gas Dry

Molecular W eight M d 30.5 30.5 30.5
Stack Gas W et Molecular

We ight M s lb/lb m ole 28.84 28.82 28.84 Actual Average Velocity (Vs) Vs ft/sec 72.37 74.67 75.08 Stack Diameter inches 101 x 43 101 x 43 101 x 43 Stack Area A sq ft 30.16 30.16 30.16 Standard Stack Gas Volumetric

Flow Q sd Standard Dry Cubic Feet/min 74856.4 77136.6 77468.7
Nozzle Diam eter inches 0.220 0.191 0.191 Nozzle Area sq ft 0.000263981 0.00019897 0.00019897 Sam ple Time mi n 180 180 182 Iso-kenetics % 98.28 103.85 100.55 SteamOutput k-lbs steam/hr 246.20 246.00 246.00 ug 112.00 124.00 205.00 HCN mg 0.112 0.124 0.205 mg/dscf 0.000971 0.001309 0.002201 ug/dscf 0.970520 1.309211 2.201433 ug/dscm 0.027493 0.037088 0.062364 ppm 0.000023 0.000031 0.000052 lb/hr 0.010 0.013 0.023 #/k-lbs steam 0.000 0.00005 0.00009 lb/MMBtu 0.000029 0.000039 0.000066

m* ppm= (0.0224)(ug/m^3) HCN EmissionsAlaska Source

LLC Testing Golden Valley Electric Association EPA ICR Request May 2010

m = 27.0254 g/mol for HCNAlaska Source

LLC Testing Golden Valley Electric Association EPA ICR Request May 2010

did not deduct run blank (12.3)