### T [F]: Ambient Temperature **NetCapacity [Btu/hr] = NetCapcity-CoeffcientA*T+NetCapcity-CoeffcientB** **Compr [W] = Cmpr-CoeffcientA*T+Cmpr-CoeffcientB** **Cond Fan Power [W] = (T-95)*CondFanCoefficient*CondFanPower@95+CondFanPower@95** **Indoor Fan and Control power do not vary with ambient**

**7.5-ton correlations based on external static pressure from DOE's test procedure**

SingleCompressor Baselinev1-Stage-1 DualCompressor

Baseline-v2-Stage-1 DualCompressor Baseline-v2-Stage-2 P1-EL1-Stage-1P1-EL1-Stage-2P1-EL2-Stage-1P1-EL2-Stage-2

NetCapcity-CoeffcientA -367.7989756 -194.8060928 -401.1778262 -256.3541374-436.6196509-287.3200871 -449.6722901 NetCapcity-CoeffcientB 125308.3244 57865.17247 125170.6917 69415.72693 129789.4599 74821.38267 134595.9477 Cmpr-CoeffcientA 43.52378533 39.38138952 71.58635639 28.77126939 54.33002322 28.55380835 58.62401821 Cmpr-CoeffcientB 2735.341995 -113.8833184 -225.4036676 156.7971444 217.0828953 -106.0667861 -206.6670831
Cond Fan Coefficient -0.001186551 -0.001186551 -0.001186551 -0.001186551-0.001186551-0.001186551 -0.001186551 Cond Fan Power @ 95F [W] 520.00 452.00 452.00 800.00 800.00 640.00 640.00 Indoor Fan [W] 735.97 674.65 674.65 742.39 742.39 970.00 970.00 Control [W] 17.00 16.00 21.00 16.00 21.00 16.00 21.00

P1-EL2.5-Stage-1 P1-EL2.5-Stage-2 P1-EL2.5-Stage-3 EL3-Stage-1 EL3-Stage-2 EL3-Stage-3 EL3.5-Stage-1 EL3.5-Stage-2 NetCapcity-CoeffcientA -196.4544974 -244.1706349 -409.7110283 -214.3804871-252.1869672-424.3803428 -251.6753107 -449.6722901 NetCapcity-CoeffcientB 55218.71117 76713.10086 128441.9286 61252.4892 83563.25077 140266.2405 72105.29051 134595.9477 Cmpr-CoeffcientA 26.37629152 42.75983836 65.08748865 30.35507856 44.75304547 73.33750838 28.06030824 58.62401821 Cmpr-CoeffcientB -189.2922124 -327.1212177 -448.7602958 -299.0521184-75.14922066-414.3965748 -101.0759691 -206.6670831
Cond Fan Coefficient -0.001186551 -0.001186551 -0.001186551 -0.001186551-0.001186551-0.001186551 -0.001186551 -0.001186551 Cond Fan Power @ 95F [W] 702.70 702.70 702.70 704.50 704.50 704.50 640.00 640.00 Indoor Fan [W] 295.00 295.00 585.00 310.40 310.40 623.00 528.45 970.00 Control [W] 24.00 24.00 32.00 24.00 24.00 32.00 20.00 24.00

EL4-Stage-1 EL4-Stage-2 EL4-Stage-3 EL5-Stage-1 EL5-Stage-2 P2-EL1-Stage-1P2-EL1-Stage-2 P2-EL2-Stage-1P2-EL2-Stage-2 NetCapcity-CoeffcientA -172.9085837 -267.3547697 -411.5468133 -248.3482403-432.4396024-171.1614738 -381.0588876 -237.7607842 -435.6833977 NetCapcity-CoeffcientB 52306.36847 85646.55079 128669.7174 73904.51571 133158.1627 56760.41683 119237.9959 67593.47037 130926.0401 Cmpr-CoeffcientA 21.22532778 36.84561469 62.2974021 26.72819648 56.16330142 31.69838198 62.61691266 30.95060876 54.83030286 Cmpr-CoeffcientB -228.5479718 -312.4964451 -375.2050637 -81.55589018 16.2091654 132.066308 301.5882408 139.2855669 218.6508979
Cond Fan Coefficient -0.001186551 -0.001186551 -0.001186551 -0.001186551-0.001186551-0.001186551 -0.001186551 -0.001186551 -0.001186551 Cond Fan Power @ 95F [W] 344.00 467.67 781.33 150.00 650.00 667.00 667.00 800.00 800.00 Indoor Fan [W] 196.89 196.89 402.23 252.78 513.80 195.11 531.00 274.85 748.00 Control [W] 24.00 24.00 40.00 24.00 40.00 20.00 24.00 20.00 24.00

## T [F]: Ambient Temperature **NetCapacity [Btu/hr] = NetCapcity-CoeffcientA*T+NetCapcity-CoeffcientB** **Compr [W] = Cmpr-CoeffcientA*T+Cmpr-CoeffcientB** **Cond Fan Power [W] = (T-95)*CondFanCoefficient*CondFanPower@95+CondFanPower@95** **Indoor Fan and Control power do not vary with ambient**

**15-ton correlations based on external static pressure from DOE's test procedure**

Baseline-Stage-1Baseline-Stage-2P1-EL1-Stage-1P1-EL1-Stage-2P1-EL2-Stage-1P1-EL2-Stage-2P1-EL2.5-Stage-1P1-EL2.5-Stage-2 NetCapcity-CoeffcientA -415.581941 -702.4932682 -504.3280607 -769.859114 -584.2712513-751.7632331 -490.6048619 -754.3242769 NetCapcity-CoeffcientB 123148.5327 243141.4228 164309.3997 250510.6909 143491.2427 249338.5359 156203.0158 244067.9482 Cmpr-CoeffcientA 63.18587482 122.249491 88.84238907 137.2219404 51.2173176 113.9917323 92.16668539 128.2739883 Cmpr-CoeffcientB 1210.728333 1821.431619 581.4532074 496.4948912 1558.158852 1919.290811 -518.8502638 -604.6998354
Cond Fan Coefficient -0.001186551 -0.001186551 -0.001186551-0.001186551-0.001186551-0.001186551 -0.001186551 -0.001186551 Cond Fan Power @ 95F [W] 1100.00 1100.00 1177.00 1177.00 823.58 823.58 1500.00 1500.00 Indoor Fan [W] 1340.00 1340.00 1140.00 1140.00 1139.32 1139.32 464.44 1264.00 Control [W] 16.00 21.00 16.00 21.00 16.00 21.00 16.00 21.00

EL3-Stage-1 EL3-Stage-2 EL3-Stage-3 EL3.5-Stage-1 EL3.5-Stage-2 EL3.5-Stage-3 EL4-Stage-1 EL4-Stage-2 EL4-Stage-3 NetCapcity-CoeffcientA -314.6032251 -538.7330825 -793.7706408 -311.601261 -562.6313199-801.9134969 -292.5878712 -545.0809881 -801.8575384 NetCapcity-CoeffcientB 97399.21944 160835.6092 247274.2486 99494.05527 166406.499 250434.9427 95455.16435 168177.9439 250130.6414 Cmpr-CoeffcientA 43.53318326 79.81579486 116.9781142 41.45542454 76.53507845 116.8767765 41.03814624 68.96839991 111.61365 Cmpr-CoeffcientB 34.48485612 1059.715988 894.8119875 48.48400623 1048.442052 921.2059753 -27.97585888 957.1685867 1149.540574
Cond Fan Coefficient -0.001186551 -0.001186551 -0.001186551-0.001186551-0.001186551-0.001186551 -0.001186551 -0.001186551 -0.001186551 Cond Fan Power @ 95F [W] 1097.00 1097.00 1097.00 1097.00 1097.00 1097.00 405.00 550.67 920.00 Indoor Fan [W] 413.60 413.60 1107.50 403.99 403.99 1099.47 182.33 274.57 921.54 Control [W] 24.00 24.00 32.00 24.00 24.00 32.00 24.00 24.00 40.00

EL5-Stage-1 EL5-Stage-2 EL5-Stage-3 EL5-Stage-4 P2-EL1-Stage-1P2-EL1-Stage-2P2-EL2-Stage-1 P2-EL2-Stage-2 NetCapcity-CoeffcientA -227.5483272 -400.2961808 -499.7138212-738.7778436-365.4309076-740.0976324 -557.0238604 -776.9001164 NetCapcity-CoeffcientB 55925.9828 115709.2128 166980.4321 241006.026 118108.4628 242467.5004 175357.3951 250919.2369 Cmpr-CoeffcientA 27.32029961 57.3919883 80.06886317 126.7156471 65.10905917 124.0923678 94.32372287 134.2154849 Cmpr-CoeffcientB -1086.866507 -1133.435057 -626.3615887-980.6545713 1186.395995 2034.543464 850.6934581 659.5344999
Cond Fan Coefficient -0.001186551 -0.001186551 -0.001186551-0.001186551-0.001186551-0.001186551 -0.001186551 -0.001186551 Cond Fan Power @ 95F [W] 482.80 482.80 482.80 1097.00 757.00 757.00 1177.00 1177.00 Indoor Fan [W] 420.74 420.74 420.74 1098.00 454.54 1277.00 451.75 1255.00 Control [W] 80.00 80.00 80.00 96.00 24.00 32.00 24.00 32.00