Facility _Information

facility _id utility

_code legal_owner_name

legl_operator_name

legal_address_type

legal_address

legal_city legal_state legal_zip 55318 50096 RRI Energy Florida, LLC RRI Energy

Florida, LLC operator 1000 Main St Houston TX 77022

Page 1Facility _Information

plant_name

physical_address

phyical_city

physical_state

physical_zip

mailing_address

mailing_city

mailing_state

mailing_zip Indian River

7800 South US Highway 1 Titusville FL 32780 7800 South US Highway 1 Titusville FL 32780

Page 2Facility _Information

RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas No FALSE TRUE TRUE FALSE TRUE FALSE TRUE TRUE

Page 3Facility _Information

ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE TRUE Title V Operating Permit No. 0090196-011-AV, Condition II.FW8 Annual Statement of Compliance. The permittee shall submit an annual statement of compliance to the compliance authority at the address shown on the cover of this permit within 60 days after the end of each calendar year during which the Title V permit was effective. [Rules 62-213.440(3)(a)2. & 3. and (b), F.A.C.] Title V Operating Permit No. 0090196-011-AV, Condition III.A.29 Quarterly Excess Emissions Reporting Requirements. Submit to the Department a written report of emissions in excess of emission limiting standards as set forth in Rule 62-296.405(1), F.A.C., for each calendar quarter. The nature and cause of the excess emissions s No USEPA Clean Air Markets The MWe net (summer) unit 3 = 319.6The detail on the composition by volume or heating value for different fuel types for the reported tests is not available. The type of fuel during tests was selected to be oil-distillate and oil-residual for units 1 and 2 as it is possible that both types of oil were burned. Note that these units have combusted more than 90% residual oil by both volume and heating value in the time period 2007-2009. Unit 3 did not burned distillate oil in calendar years 2005, 2006, 2007, 2008, 2009.All particulate concentrations measured in gr/dscf.Stack TempsIIR1-PM-SS-2005Run 1 - 325.1Run 2 - 326.2Run 3 - 324.1IR1-PM-SB-2005Run 1 - 318.2Run 2 - 321.7Run 3 - 324.2IR1-PM-SS-2006Run 1 - 328.1Run 2 - 335.1Run 3 - 332.8IR1-PM-SB-2006Run 1 - 331.1Run 2 - 334.4Run 3 - 338IR1-PM-SS-2007Run 1 - 334Run 2 - 324.2Run 3 - 327.8IR1-PM-SB-2007Run 1 - 328.8Run 2 - 332.7Run 3 - 332.1IR2-PM-SS-2005Run 1 - 330Run 2 - 334R

Page 4Facility _Information

The MWe net (summer) unit 3 = 319.6The detail on the composition by volume or heating value for different fuel types for the reported tests is not available. The type of fuel during tests was selected to be oil-distillate and oil-residual for units 1 and 2 as it is possible that both types of oil were burned. Note that these units have combusted more than 90% residual oil by both volume and heating value in the time period 2007-2009. Unit 3 did not burned distillate oil in calendar years 2005, 2006, 2007, 2008, 2009.All particulate concentrations measured in gr/dscf.Stack TempsIIR1-PM-SS-2005Run 1 - 325.1Run 2 - 326.2Run 3 - 324.1IR1-PM-SB-2005Run 1 - 318.2Run 2 - 321.7Run 3 - 324.2IR1-PM-SS-2006Run 1 - 328.1Run 2 - 335.1Run 3 - 332.8IR1-PM-SB-2006Run 1 - 331.1Run 2 - 334.4Run 3 - 338IR1-PM-SS-2007Run 1 - 334Run 2 - 324.2Run 3 - 327.8IR1-PM-SB-2007Run 1 - 328.8Run 2 - 332.7Run 3 - 332.1IR2-PM-SS-2005Run 1 - 330Run 2 - 334R

Page 5Facility _Information

The MWe net (summer) unit 3 = 319.6The detail on the composition by volume or heating value for different fuel types for the reported tests is not available. The type of fuel during tests was selected to be oil-distillate and oil-residual for units 1 and 2 as it is possible that both types of oil were burned. Note that these units have combusted more than 90% residual oil by both volume and heating value in the time period 2007-2009. Unit 3 did not burned distillate oil in calendar years 2005, 2006, 2007, 2008, 2009.All particulate concentrations measured in gr/dscf.Stack TempsIIR1-PM-SS-2005Run 1 - 325.1Run 2 - 326.2Run 3 - 324.1IR1-PM-SB-2005Run 1 - 318.2Run 2 - 321.7Run 3 - 324.2IR1-PM-SS-2006Run 1 - 328.1Run 2 - 335.1Run 3 - 332.8IR1-PM-SB-2006Run 1 - 331.1Run 2 - 334.4Run 3 - 338IR1-PM-SS-2007Run 1 - 334Run 2 - 324.2Run 3 - 327.8IR1-PM-SB-2007Run 1 - 328.8Run 2 - 332.7Run 3 - 332.1IR2-PM-SS-2005Run 1 - 330Run 2 - 334R

Page 6Facility _Information

The MWe net (summer) unit 3 = 319.6The detail on the composition by volume or heating value for different fuel types for the reported tests is not available. The type of fuel during tests was selected to be oil-distillate and oil-residual for units 1 and 2 as it is possible that both types of oil were burned. Note that these units have combusted more than 90% residual oil by both volume and heating value in the time period 2007-2009. Unit 3 did not burned distillate oil in calendar years 2005, 2006, 2007, 2008, 2009.All particulate concentrations measured in gr/dscf.Stack TempsIIR1-PM-SS-2005Run 1 - 325.1Run 2 - 326.2Run 3 - 324.1IR1-PM-SB-2005Run 1 - 318.2Run 2 - 321.7Run 3 - 324.2IR1-PM-SS-2006Run 1 - 328.1Run 2 - 335.1Run 3 - 332.8IR1-PM-SB-2006Run 1 - 331.1Run 2 - 334.4Run 3 - 338IR1-PM-SS-2007Run 1 - 334Run 2 - 324.2Run 3 - 327.8IR1-PM-SB-2007Run 1 - 328.8Run 2 - 332.7Run 3 - 332.1IR2-PM-SS-2005Run 1 - 330Run 2 - 334R

Page 7Facility _Information

The MWe net (summer) unit 3 = 319.6The detail on the composition by volume or heating value for different fuel types for the reported tests is not available. The type of fuel during tests was selected to be oil-distillate and oil-residual for units 1 and 2 as it is possible that both types of oil were burned. Note that these units have combusted more than 90% residual oil by both volume and heating value in the time period 2007-2009. Unit 3 did not burned distillate oil in calendar years 2005, 2006, 2007, 2008, 2009.All particulate concentrations measured in gr/dscf.Stack TempsIIR1-PM-SS-2005Run 1 - 325.1Run 2 - 326.2Run 3 - 324.1IR1-PM-SB-2005Run 1 - 318.2Run 2 - 321.7Run 3 - 324.2IR1-PM-SS-2006Run 1 - 328.1Run 2 - 335.1Run 3 - 332.8IR1-PM-SB-2006Run 1 - 331.1Run 2 - 334.4Run 3 - 338IR1-PM-SS-2007Run 1 - 334Run 2 - 324.2Run 3 - 327.8IR1-PM-SB-2007Run 1 - 328.8Run 2 - 332.7Run 3 - 332.1IR2-PM-SS-2005Run 1 - 330Run 2 - 334R

Page 8Facility _Information

The MWe net (summer) unit 3 = 319.6The detail on the composition by volume or heating value for different fuel types for the reported tests is not available. The type of fuel during tests was selected to be oil-distillate and oil-residual for units 1 and 2 as it is possible that both types of oil were burned. Note that these units have combusted more than 90% residual oil by both volume and heating value in the time period 2007-2009. Unit 3 did not burned distillate oil in calendar years 2005, 2006, 2007, 2008, 2009.All particulate concentrations measured in gr/dscf.Stack TempsIIR1-PM-SS-2005Run 1 - 325.1Run 2 - 326.2Run 3 - 324.1IR1-PM-SB-2005Run 1 - 318.2Run 2 - 321.7Run 3 - 324.2IR1-PM-SS-2006Run 1 - 328.1Run 2 - 335.1Run 3 - 332.8IR1-PM-SB-2006Run 1 - 331.1Run 2 - 334.4Run 3 - 338IR1-PM-SS-2007Run 1 - 334Run 2 - 324.2Run 3 - 327.8IR1-PM-SB-2007Run 1 - 328.8Run 2 - 332.7Run 3 - 332.1IR2-PM-SS-2005Run 1 - 330Run 2 - 334R

Page 9Facility _Information

The MWe net (summer) unit 3 = 319.6The detail on the composition by volume or heating value for different fuel types for the reported tests is not available. The type of fuel during tests was selected to be oil-distillate and oil-residual for units 1 and 2 as it is possible that both types of oil were burned. Note that these units have combusted more than 90% residual oil by both volume and heating value in the time period 2007-2009. Unit 3 did not burned distillate oil in calendar years 2005, 2006, 2007, 2008, 2009.All particulate concentrations measured in gr/dscf.Stack TempsIIR1-PM-SS-2005Run 1 - 325.1Run 2 - 326.2Run 3 - 324.1IR1-PM-SB-2005Run 1 - 318.2Run 2 - 321.7Run 3 - 324.2IR1-PM-SS-2006Run 1 - 328.1Run 2 - 335.1Run 3 - 332.8IR1-PM-SB-2006Run 1 - 331.1Run 2 - 334.4Run 3 - 338IR1-PM-SS-2007Run 1 - 334Run 2 - 324.2Run 3 - 327.8IR1-PM-SB-2007Run 1 - 328.8Run 2 - 332.7Run 3 - 332.1IR2-PM-SS-2005Run 1 - 330Run 2 - 334R

Page 10Facility _Information

The MWe net (summer) unit 3 = 319.6The detail on the composition by volume or heating value for different fuel types for the reported tests is not available. The type of fuel during tests was selected to be oil-distillate and oil-residual for units 1 and 2 as it is possible that both types of oil were burned. Note that these units have combusted more than 90% residual oil by both volume and heating value in the time period 2007-2009. Unit 3 did not burned distillate oil in calendar years 2005, 2006, 2007, 2008, 2009.All particulate concentrations measured in gr/dscf.Stack TempsIIR1-PM-SS-2005Run 1 - 325.1Run 2 - 326.2Run 3 - 324.1IR1-PM-SB-2005Run 1 - 318.2Run 2 - 321.7Run 3 - 324.2IR1-PM-SS-2006Run 1 - 328.1Run 2 - 335.1Run 3 - 332.8IR1-PM-SB-2006Run 1 - 331.1Run 2 - 334.4Run 3 - 338IR1-PM-SS-2007Run 1 - 334Run 2 - 324.2Run 3 - 327.8IR1-PM-SB-2007Run 1 - 328.8Run 2 - 332.7Run 3 - 332.1IR2-PM-SS-2005Run 1 - 330Run 2 - 334R

Page 11Facility _Information

The MWe net (summer) unit 3 = 319.6The detail on the composition by volume or heating value for different fuel types for the reported tests is not available. The type of fuel during tests was selected to be oil-distillate and oil-residual for units 1 and 2 as it is possible that both types of oil were burned. Note that these units have combusted more than 90% residual oil by both volume and heating value in the time period 2007-2009. Unit 3 did not burned distillate oil in calendar years 2005, 2006, 2007, 2008, 2009.All particulate concentrations measured in gr/dscf.Stack TempsIIR1-PM-SS-2005Run 1 - 325.1Run 2 - 326.2Run 3 - 324.1IR1-PM-SB-2005Run 1 - 318.2Run 2 - 321.7Run 3 - 324.2IR1-PM-SS-2006Run 1 - 328.1Run 2 - 335.1Run 3 - 332.8IR1-PM-SB-2006Run 1 - 331.1Run 2 - 334.4Run 3 - 338IR1-PM-SS-2007Run 1 - 334Run 2 - 324.2Run 3 - 327.8IR1-PM-SB-2007Run 1 - 328.8Run 2 - 332.7Run 3 - 332.1IR2-PM-SS-2005Run 1 - 330Run 2 - 334R

Page 12Facility _Information

The MWe net (summer) unit 3 = 319.6The detail on the composition by volume or heating value for different fuel types for the reported tests is not available. The type of fuel during tests was selected to be oil-distillate and oil-residual for units 1 and 2 as it is possible that both types of oil were burned. Note that these units have combusted more than 90% residual oil by both volume and heating value in the time period 2007-2009. Unit 3 did not burned distillate oil in calendar years 2005, 2006, 2007, 2008, 2009.All particulate concentrations measured in gr/dscf.Stack TempsIIR1-PM-SS-2005Run 1 - 325.1Run 2 - 326.2Run 3 - 324.1IR1-PM-SB-2005Run 1 - 318.2Run 2 - 321.7Run 3 - 324.2IR1-PM-SS-2006Run 1 - 328.1Run 2 - 335.1Run 3 - 332.8IR1-PM-SB-2006Run 1 - 331.1Run 2 - 334.4Run 3 - 338IR1-PM-SS-2007Run 1 - 334Run 2 - 324.2Run 3 - 327.8IR1-PM-SB-2007Run 1 - 328.8Run 2 - 332.7Run 3 - 332.1IR2-PM-SS-2005Run 1 - 330Run 2 - 334R

Page 13Facility _Information

The MWe net (summer) unit 3 = 319.6The detail on the composition by volume or heating value for different fuel types for the reported tests is not available. The type of fuel during tests was selected to be oil-distillate and oil-residual for units 1 and 2 as it is possible that both types of oil were burned. Note that these units have combusted more than 90% residual oil by both volume and heating value in the time period 2007-2009. Unit 3 did not burned distillate oil in calendar years 2005, 2006, 2007, 2008, 2009.All particulate concentrations measured in gr/dscf.Stack TempsIIR1-PM-SS-2005Run 1 - 325.1Run 2 - 326.2Run 3 - 324.1IR1-PM-SB-2005Run 1 - 318.2Run 2 - 321.7Run 3 - 324.2IR1-PM-SS-2006Run 1 - 328.1Run 2 - 335.1Run 3 - 332.8IR1-PM-SB-2006Run 1 - 331.1Run 2 - 334.4Run 3 - 338IR1-PM-SS-2007Run 1 - 334Run 2 - 324.2Run 3 - 327.8IR1-PM-SB-2007Run 1 - 328.8Run 2 - 332.7Run 3 - 332.1IR2-PM-SS-2005Run 1 - 330Run 2 - 334R

Page 14Facility _Information

The MWe net (summer) unit 3 = 319.6The detail on the composition by volume or heating value for different fuel types for the reported tests is not available. The type of fuel during tests was selected to be oil-distillate and oil-residual for units 1 and 2 as it is possible that both types of oil were burned. Note that these units have combusted more than 90% residual oil by both volume and heating value in the time period 2007-2009. Unit 3 did not burned distillate oil in calendar years 2005, 2006, 2007, 2008, 2009.All particulate concentrations measured in gr/dscf.Stack TempsIIR1-PM-SS-2005Run 1 - 325.1Run 2 - 326.2Run 3 - 324.1IR1-PM-SB-2005Run 1 - 318.2Run 2 - 321.7Run 3 - 324.2IR1-PM-SS-2006Run 1 - 328.1Run 2 - 335.1Run 3 - 332.8IR1-PM-SB-2006Run 1 - 331.1Run 2 - 334.4Run 3 - 338IR1-PM-SS-2007Run 1 - 334Run 2 - 324.2Run 3 - 327.8IR1-PM-SB-2007Run 1 - 328.8Run 2 - 332.7Run 3 - 332.1IR2-PM-SS-2005Run 1 - 330Run 2 - 334R

Page 15facility _contacts

facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 55318 1 Air Quality Specialist III Sharene Shealey

7245978232

7242553220

sshealey@rrienergy.com

TRUE 55318 2 Manager Keith A. Schm idt 7245978193 kschmidt@rrienergy.com FALSE

Page 16facility _coal_utilized

facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note

Page 17facility _oil_utilized

facility _id oil_type percentage_volume percentage_btu

other_type 55318 No.2 Fuel Oil (distillate) 0.66 0.6 55318 No.6 Fuel Oil (residual or bunker C) 99.34 99.4

Page 18facility _other_materials

facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain 55318 On-Spec Used Oil

TRUE TRUE 293 num ber/year The amount reported is the average of the amounts combusted in the years 2007, 2008, and 2009. The measurement unit is "gallons/year".

No No determination has been made regarding whether on-spec used oil would be burned in this unit if the used oil were subject to CAA section 129. "No" was selected as the response because "Undetermined" is not an available choice.

Page 19facility _other_materials

rcra_explain No determination has been made regarding whether on-spec used oil would be burned in this unit if the used oil were subject to CAA section 129. "No" was selected as the response because "Undetermined" is not an available choice.

Page 20facility _other_materials

No determination has been made regarding whether on-spec used oil would be burned in this unit if the used oil were subject to CAA section 129. "No" was selected as the response because "Undetermined" is not an available choice.

Page 21facility _other_materials

No determination has been made regarding whether on-spec used oil would be burned in this unit if the used oil were subject to CAA section 129. "No" was selected as the response because "Undetermined" is not an available choice.

Page 22boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuelheat_input max_heat_input MWe_capacity 55318 1 Tangential firing fuel oil 865.5 923.3 79 55318 2 Tangential firing fuel oil 2248.7 2248.7 213 55318 3 Tangential firing fuel oil 3408.5 3409.7 317

Page 23boiler_information

MWe_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 75.6 31.1 24.9 1800 1800 1000 1000 FALSE 1000 181.1 32.3 26.4 1800 1800 1000 1000 FALSE 1000 0 33.7 30.5 1800 1800 1000 1000 FALSE 1000

Page 24boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 1000 1111.67 4.5 N FALSE FALSE 1000 940.67 3.3 N FALSE FALSE 1000 1038.33 4.3 N FALSE

Page 25boiler_information

NOx_control

SO2_control

combustion_additives No No No No No No No No No

Page 26boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 55318 1 natural gas 2007 0 75 55318 1 natural gas 2008 0 85.4 55318 1 natural gas 2009 0 91.1 55318 1 oil - distillate 2007 1.4 0.3 55318 1 oil - distillate 2008 4.2 0.6 55318 1 oil - distillate 2009 6.3 0.5 55318 1 oil - residual or bunker 2007 98.6 24.7 55318 1 oil - residual or bunker 2008 95.8 14 55318 1 oil - residual or bunker 2009 93.7 8.4 55318 2 natural gas 2007 0 50.5 55318 2 natural gas 2008 0 67.7 55318 2 natural gas 2009 0 94 55318 2 oil - distillate 2007 0.33 0.1 55318 2 oil - distillate 2008 1.1 0.3 55318 2 oil - distillate 2009 3.7 0.2 55318 2 oil - other 2007 0.03 0 on-spec used oil 55318 2 oil - residual or bunker 2007 99.64 49.4 55318 2 oil - residual or bunker 2008 98.9 32 55318 2 oil - residual or bunker 2009 96.3 5.8 55318 3 natural gas 2007 0 55.5 55318 3 natural gas 2008 0 59.9 55318 3 natural gas 2009 0 65.5 55318 3 oil - residual or bunker 2007 100 44.5 55318 3 oil - residual or bunker 2008 100 40.1 55318 3 oil - residual or bunker 2009 100 34.5

Page 27boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online

Page 28boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online

Page 29boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 30facility _units

facility _id unit_id 55318 1 55318 2 55318 3

Page 31unit_boilers

facility _id unit_id boiler_id 55318 1 1 55318 2 2 55318 3 3

Page 32facility _controls

facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent

Page 33facility _controls

reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive

Page 34facility _sampling_ports

facility _id sampling_port_id 55318 1A-common stack 55318 1B-common stack 55318 1C-common stack 55318 1D-common stack 55318 3A-unit 3 stack 55318 3B-unit 3 stack 55318 3C-unit 3 stack 55318 3D-unit 3 stack

Page 35facility _stacks

facility _id stack_id stack_height stack_diameter

sack_gas_velocity 55318 CS-1 298 14.05 55318 S3 298 14.09

Page 36configurations

facility _id configuration_id 55318 IR-1 55318 IR-2 55318 IR-3

Page 37configuration_components

facility _id configuration_id

component_id

order component_type port_near 55318 IR-1 1 1 Unit 55318 IR-1 1A-common stack 2 Sam pling Port pevious 55318 IR-1 1B-common stack 2 Sam pling Port pevious 55318 IR-1 1C-common stack 2 Sam pling Port pevious 55318 IR-1 1D-common stack 2 Sam pling Port pevious 55318 IR-1 CS-1 2 Stack 55318 IR-2 1A-common stack 2 Sam pling Port pevious 55318 IR-2 1B-common stack 2 Sam pling Port pevious 55318 IR-2 1C-common stack 2 Sam pling Port pevious 55318 IR-2 1D-common stack 2 Sam pling Port pevious 55318 IR-2 2 1 Unit 55318 IR-2 CS-1 2 Stack 55318 IR-3 3 1 Unit 55318 IR-3 3A-unit 3 stack 2 Sam pling Port pevious 55318 IR-3 3B-unit 3 stack 2 Sam pling Port pevious 55318 IR-3 3C-unit 3 stack 2 Sam pling Port pevious 55318 IR-3 3D-unit 3 stack 2 Sam pling Port pevious 55318 IR-3 S3 2 Stack

Page 38configuration_pollutants1

facility _id configuration_id

pollutant_name

permit_type_1

emlim it_1 emlim it_units_1 avg_period_1

emlim it_2 emlim it_units_2 55318 IR-1 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

3 hours 0.3 pound per million British Thermal Unit (lb/MMBtu) 55318 IR-1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

2.75 pound per million British Thermal Unit (lb/MMBtu)

daily 55318 IR-2 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

3 hours 0.3 pound per million British Thermal Unit (lb/MMBtu) 55318 IR-2 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

2.75 pound per million British Thermal Unit (lb/MMBtu)

daily 55318 IR-3 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

3 hours 0.3 pound per million British Thermal Unit (lb/MMBtu) 55318 IR-3 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

2.75 pound per million British Thermal Unit (lb/MMBtu)

daily

Page 39configuration_pollutants1

avg_period_2

emlim it_3 emlim it_units_3 avg_period_3

emlim it_4 emlim it_units_4 avg_period_4

emlim it_details

test_method 3 hours The 0.1 lb/mmBtu limit is during non-soot blowing operations. The 0.3 lb/mmBtu limit is during soot-blowing operations.Compliance with the filterable PM limit is determined by the average of three 1-hour test runs. EPA RM5 or RM17

3 hours The 0.1 lb/mmBtu limit is during non-soot blowing operations. The 0.3 lb/mmBtu limit is during soot-blowing operations.Compliance with the filterable PM limit is determined by the average of three 1-hour test runs. EPA RM5 or RM17

3 hours The 0.1 lb/mmBtu limit is during non-soot blowing operations. The 0.3 lb/mmBtu limit is during soot-blowing operations.Compliance with the filterable PM limit is determined by the average of three 1-hour test runs. EPA RM5 or RM17

Page 40configuration_pollutants1

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping

req_reporting EPA RM5 or RM17 Performance of annual compliance test if unit operates > 400 hours while firing oil. Heat Input per per 40 CFR 75.

Subm ittal of stack test report. Perform daily

sulfur content analysis of as-fired fuels (data from natural gas supplier is acceptable). Per 40 CFR 75 requirements.

Quarterly

EDRs to EPA; Quarterly deviations reports to FL DEP. EPA RM5 or RM17 Performance of annual compliance test if unit operates > 400 hours while firing oil. Heat Input per per 40 CFR 75.

Subm ittal of stack test report. Perform daily

sulfur content analysis of as-fired fuels (data from natural gas supplier is acceptable). Per 40 CFR 75 requirements.

Quarterly

EDRs to EPA; Quarterly deviations reports to FL DEP. EPA RM5 or RM17 Performance of annual compliance test if unit operates > 400 hours while firing oil. Heat Input per per 40 CFR 75.

Subm ittal of stack test report. Perform daily

sulfur content analysis of as-fired fuels (data from natural gas supplier is acceptable). Per 40 CFR 75 requirements.

Quarterly

EDRs to EPA; Quarterly deviations reports to FL DEP.

Page 41configuration_pollutants1

Quarterly

EDRs to EPA; Quarterly deviations reports to FL DEP.

Quarterly

EDRs to EPA; Quarterly deviations reports to FL DEP.

Quarterly

EDRs to EPA; Quarterly deviations reports to FL DEP.

Page 42control_technologies

facility _id configuration_id

component_id

control_id project_titleproject_type vendor_name

vndor_contact

vendor_phone

Page 43control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 44control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 45control_technologies

feed_rate_units

Page 46control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 47control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_name

Page 48control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investment

total_operating_costs

base_year

Page 49control_costs

CBI

Page 50misc_controls

facility _id misc_control_id

control_description

Page 51misc_control_configurations

facility _id misc_control_id

configuration_id

Page 52fuel_shipments

facility _id shipment_id

shipment_date

amount_received

amount_units

fuel_type state_country other_country

county

Page 53fuel_shipments

coal_seam shipment_method

Page 54fuel_shipment_configurations

facility _id shipment_id

configuration_id

Page 55fuel_shipment_samples

facility _id shipment_id

sample_id amount_fuel amount_fuel_units

total_sulfur ash_content heating_value

hating_units

Page 56fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address

Page 57fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_name lab_address lab_city lab_state lab_zip analysis_copies

Page 58fuel_shipment_samples

analysis_copies

Page 59fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL

Page 60test_reports

facility _id report_id report_typeother_type report_description report_begin_date

report_end_date

before_control

during_deviation 55318 IR1-PM-SB-2005

compliance Particulate compliance testing while soot blowing 4/7/2005 4/7/2005 No No 55318 IR1-PM-SB-2006

compliance Particulate compliance testing while soot blowing 6/21/2006 6/21/2006 No No 55318 IR1-PM-SB-2007

compliance Particulate compliance testing while soot blowing 8/8/2007 8/8/2007 No No 55318 IR1-PM-SS-2005

compliance Particulate compliance testing while running at steady state 4/7/2005 4/7/2005 No No 55318 IR1-PM-SS-2006

compliance Particulate compliance testing while running at steady state 6/21/2006 6/21/2006 No No 55318 IR1-PM-SS-2007

compliance Particulate compliance testing while running at steady state 8/8/2007 8/8/2007 No No 55318 IR2-PM-SB-2005

compliance Particulate compliance testing while soot blowing 6/7/2005 6/7/2005 No No 55318 IR2-PM-SB-2007

compliance Particulate compliance testing while soot blowing 9/12/2007 9/12/2007 No No 55318 IR2-PM-SS-2005

compliance Particulate compliance testing while operating at steady state 6/7/2005 6/7/2005 No No 55318 IR2-PM-SS-2007

compliance Particulate compliance testing while operating at steady state 9/12/2007 9/12/2007 No No 55318 IR3-PM-SB-2005

compliance Particulate compliance testing while the unit was soot blowing 7/21/2005 7/21/2005 No No 55318 IR3-PM-SB-2006

compliance Particulate compliance testing while the unit was soot blowing 6/20/2006 6/20/2006 No No 55318 IR3-PM-SB-2007

compliance Particulate compliance testing while the unit was soot blowing 9/11/2007 9/11/2007 No No 55318 IR3-PM-SS-2005

compliance Particulate compliance testing while the unit was operating at steady state 7/21/2005 7/21/2005 No No 55318 IR3-PM-SS-2006

compliance Particulate compliance testing while the unit was operating at steady state 6/20/2006 6/20/2006 No No 55318 IR3-PM-SS-2007

compliance Particulate compliance testing while the unit was operating at steady state 9/11/2007 9/11/2007 No No

Page 61test_reports

deviation_reports No No No No No No No No No No No No No No No No

Page 62test_report_configurations

facility _id report_id configuration_id 55318 IR1-PM-SB-2005

IR-1 55318 IR1-PM-SB-2006

IR-1 55318 IR1-PM-SB-2007

IR-1 55318 IR1-PM-SS-2005

IR-1 55318 IR1-PM-SS-2006

IR-1 55318 IR1-PM-SS-2007

IR-1 55318 IR2-PM-SB-2005

IR-2 55318 IR2-PM-SB-2007

IR-2 55318 IR2-PM-SS-2005

IR-2 55318 IR2-PM-SS-2007

IR-2 55318 IR3-PM-SB-2005

IR-3 55318 IR3-PM-SB-2006

IR-3 55318 IR3-PM-SB-2007

IR-3 55318 IR3-PM-SS-2006

IR-3 55318 IR3-PM-SS-2007

IR-3

Page 63test_report_fuels

facility _id report_id fuel_id 55318 IR1-PM-SB-2005

Oil 55318 IR1-PM-SB-2006

Oil 55318 IR1-PM-SB-2007

Oil 55318 IR1-PM-SS-2005

Oil 55318 IR1-PM-SS-2006

Oil 55318 IR1-PM-SS-2007

Oil 55318 IR2-PM-SB-2005

Oil 55318 IR2-PM-SB-2007

Oil 55318 IR2-PM-SS-2005

Oil 55318 IR2-PM-SS-2007

Oil 55318 IR3-PM-SB-2005

Oil 55318 IR3-PM-SB-2006

Oil 55318 IR3-PM-SB-2007

Oil 55318 IR3-PM-SS-2005

Oil 55318 IR3-PM-SS-2006

Oil 55318 IR3-PM-SS-2007

Oil

Page 64test_report_fuel_types

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 55318 IR1-PM-SB-2005

Oil oil - distillate 55318 IR1-PM-SB-2005

Oil oil - residual or bunker 55318 IR1-PM-SB-2006

Oil oil - distillate 55318 IR1-PM-SB-2006

Oil oil - residual or bunker 55318 IR1-PM-SB-2007

Oil oil - distillate 55318 IR1-PM-SB-2007

Oil oil - residual or bunker 55318 IR1-PM-SS-2005

Oil oil - distillate 55318 IR1-PM-SS-2005

Oil oil - residual or bunker 55318 IR1-PM-SS-2006

Oil oil - distillate 55318 IR1-PM-SS-2006

Oil oil - residual or bunker 55318 IR1-PM-SS-2007

Oil oil - distillate 55318 IR1-PM-SS-2007

Oil oil - residual or bunker 55318 IR2-PM-SB-2005

Oil oil - distillate 55318 IR2-PM-SB-2005

Oil oil - residual or bunker 55318 IR2-PM-SB-2007

Oil oil - distillate 55318 IR2-PM-SB-2007

Oil oil - residual or bunker 55318 IR2-PM-SS-2005

Oil oil - distillate 55318 IR2-PM-SS-2005

Oil oil - residual or bunker 55318 IR2-PM-SS-2007

Oil oil - distillate 55318 IR2-PM-SS-2007

Oil oil - residual or bunker 55318 IR3-PM-SB-2005

Oil oil - residual or bunker 100 100 55318 IR3-PM-SB-2006

Oil oil - residual or bunker 100 100 55318 IR3-PM-SB-2007

Oil oil - residual or bunker 100 100 55318 IR3-PM-SS-2005

Oil oil - residual or bunker 100 100 55318 IR3-PM-SS-2006

Oil oil - residual or bunker 100 100 55318 IR3-PM-SS-2007

Oil oil - residual or bunker 100 100

Page 65cem_data

facility _id time_period

cem_period_description 55318 01/01/2005 - present

SO2 and NOx CEMS data available from 01/01/2005 to present.

Page 66cem_data_pollutants1

facility _id time_period

pollutant_name 55318 01/01/2005 - present

Nitrogen Oxide (NOx) 55318 01/01/2005 - present

Sulfur Dioxide (SO2)

Page 67test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_bypass_percent

testing_bypass_percent 55318 IR1-PM-SB-2005

CS-1 Yes Unit 1 sampling took place in the duct that feeds into the stack, which has 3 vertical ports. No 55318 IR1-PM-SB-2006

CS-1 Yes Unit 1 sampling took place in the duct that feeds into the stack, which has 3 vertical ports. No 55318 IR1-PM-SB-2007

CS-1 Yes Unit 1 sampling took place in the duct that feeds into the stack, which has 3 vertical ports. No 55318 IR1-PM-SS-2005

CS-1 Yes Unit 1 sampling took place in the duct that feeds into the stack, which has 3 vertical ports. No 55318 IR1-PM-SS-2006

CS-1 Yes Unit 1 sampling took place in the duct that feeds into the stack, which has 3 vertical ports. No 55318 IR1-PM-SS-2007

CS-1 Yes Unit 1 sampling took place in the duct that feeds into the stack, which has 3 vertical ports. No 55318 IR2-PM-SB-2005

CS-1 No No 55318 IR2-PM-SB-2007

CS-1 No No 55318 IR2-PM-SS-2005

CS-1 No No 55318 IR2-PM-SS-2007

CS-1 No No 55318 IR3-PM-SB-2005

S3 No No 55318 IR3-PM-SB-2006

S3 No No 55318 IR3-PM-SB-2007

S3 No No 55318 IR3-PM-SS-2005

S3 No No 55318 IR3-PM-SS-2006

S3 No No 55318 IR3-PM-SS-2007

S3 No No

Page 68test_report_sampling

fg_fraction

Page 69sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetime

unit_load net_generation fg_moisture_content 55318 IR1-PM-SB-2005

CS-1 1 4/7/2005 4/7/2005 8.02 55318 IR1-PM-SB-2005

CS-1 2 4/7/2005 4/7/2005 10.22 55318 IR1-PM-SB-2005

CS-1 3 4/7/2005 4/7/2005 9.39 55318 IR1-PM-SB-2006

CS-1 1 6/21/2006 6/21/2006 10.04 55318 IR1-PM-SB-2006

CS-1 2 6/21/2006 6/21/2006 9.71 55318 IR1-PM-SB-2006

CS-1 3 6/21/2006 6/21/2006 9.56 55318 IR1-PM-SB-2007

CS-1 1 8/8/2007 8/8/2007 11.17 55318 IR1-PM-SB-2007

CS-1 2 8/8/2007 8/8/2007 9.99 55318 IR1-PM-SB-2007

CS-1 3 8/8/2007 8/8/2007 9.06 55318 IR1-PM-SS-2005

CS-1 1 4/7/2005 4/7/2005 10.43 55318 IR1-PM-SS-2005

CS-1 2 4/7/2005 4/7/2005 10.62 55318 IR1-PM-SS-2005

CS-1 3 4/7/2005 4/7/2005 9.38 55318 IR1-PM-SS-2006

CS-1 1 6/21/2006 6/21/2006 10.62 55318 IR1-PM-SS-2006

CS-1 2 6/21/2006 6/21/2006 10.36 55318 IR1-PM-SS-2006

CS-1 3 6/21/2006 6/21/2006 10.65 55318 IR1-PM-SS-2007

CS-1 1 8/8/2007 8/8/2007 9.74 55318 IR1-PM-SS-2007

CS-1 2 8/8/2007 8/8/2007 8.76 55318 IR1-PM-SS-2007

CS-1 3 8/8/2007 8/8/2007 8.76 55318 IR2-PM-SB-2005

CS-1 1 6/7/2005 6/7/2005 9.12 55318 IR2-PM-SB-2005

CS-1 2 6/7/2005 6/7/2005 10.24 55318 IR2-PM-SB-2005

CS-1 3 6/7/2005 6/7/2005 8.98 55318 IR2-PM-SB-2007

CS-1 1 9/12/2007 9/12/2007 15.15 55318 IR2-PM-SB-2007

CS-1 2 9/12/2007 9/12/2007 15.56 55318 IR2-PM-SB-2007

CS-1 3 9/12/2007 9/12/2007 15.75 55318 IR2-PM-SS-2005

CS-1 1 6/7/2005 6/7/2005 10.42 55318 IR2-PM-SS-2005

CS-1 2 6/7/2005 6/7/2005 9.32 55318 IR2-PM-SS-2005

CS-1 3 6/7/2005 6/7/2005 10.52 55318 IR2-PM-SS-2007

CS-1 1 9/12/2007 9/12/2007 15.92 55318 IR2-PM-SS-2007

CS-1 2 9/12/2007 9/12/2007 16.3 55318 IR2-PM-SS-2007

CS-1 3 9/12/2007 9/12/2007 15.09 55318 IR3-PM-SB-2005

S3 1 7/21/2005 7/21/2005 12.84 55318 IR3-PM-SB-2005

S3 2 7/21/2005 7/21/2005 11.51 55318 IR3-PM-SB-2005

S3 3 7/21/2005 7/21/2005 11.31 55318 IR3-PM-SB-2006

S3 1 6/20/2006 6/20/2006 10.74 55318 IR3-PM-SB-2006

S3 2 6/20/2006 6/20/2006 7.98 55318 IR3-PM-SB-2006

S3 3 6/20/2006 6/20/2006 10.11 55318 IR3-PM-SB-2007

S3 1 9/11/2007 9/11/2007 11.11 55318 IR3-PM-SB-2007

S3 2 9/11/2007 9/11/2007 10.96 55318 IR3-PM-SB-2007

S3 3 9/11/2007 9/11/2007 9.61 55318 IR3-PM-SS-2005

S3 1 7/21/2005 7/21/2005 11.94 55318 IR3-PM-SS-2005

S3 2 7/21/2005 7/21/2005 12.2 55318 IR3-PM-SS-2005

S3 3 7/21/2005 7/21/2005 11.72 55318 IR3-PM-SS-2006

S3 1 6/20/2006 6/20/2006 10.6 55318 IR3-PM-SS-2006

S3 2 6/20/2006 6/20/2006 10.58 55318 IR3-PM-SS-2006

S3 3 6/20/2006 6/20/2006 10.82 55318 IR3-PM-SS-2007

S3 1 9/11/2007 9/11/2007 10.89 55318 IR3-PM-SS-2007

S3 2 9/11/2007 9/11/2007 11.26 55318 IR3-PM-SS-2007

S3 3 9/11/2007 9/11/2007 10.19

Page 70sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 196001.3 dscfm 0.998622 6.5 11.6 211373.2 dscfm 0.998622 6.4 11.4 215129.8 dscfm 0.998622 6 11.7 196654.2 dscfm 1.006309 6.2 11.6 197008.3 dscfm 1.006309 6.5 11.4 195054.5 dscfm 1.006309 6 11.7 183541.9 dscfm 1.005307 6.4 11.6 204254.7 dscfm 1.005307 6.4 11.4 210171 dscfm 1.005307 6.4 11.4 203580.9 dscfm 0.998622 6.4 11.3 213881.6 dscfm 0.998622 6.2 11.6 212325.3 dscfm 0.998622 5.8 11.7 192918.7 dscfm 0.998622 6.5 11.3 195431.3 dscfm 0.998622 6.4 11.4 195668.6 dscfm 0.998622 6.5 11.5 201870.7 dscfm 1.005307 6.3 11.5 208589.3 dscfm 1.005307 6.6 11.4 210086.7 dscfm 1.005307 6.4 11.4 388582.9 dscfm 0.999291 6.8 10.8 383511.5 dscfm 0.999291 6.5 11.2 387259.9 dscfm 0.999291 6.6 11.2 402786.3 dscfm 1.003636 6.1 11.4 403284.7 dscfm 1.003636 6.1 11.5 413823.2 dscfm 1.003636 6.2 11.4 378279.2 dscfm 0.999291 7 10.8 376783.2 dscfm 0.999291 6.7 11 377452.6 dscfm 0.999291 6.6 11 399114.4 dscfm 1.003636 6.1 11.5 407842.4 dscfm 1.003636 6.2 11.5 373931.8 dscfm 1.003636 6.3 11.4 665304.2 dscfm 1.005641 3.8 13.2 6688878 dscfm 1.005641 4 13 672715.9 dscfm 1.005641 4.2 12.8 734217.6 dscfm 1.004972 4.5 13.2 751549.4 dscfm 1.004972 4.7 12.5 748862.9 dscfm 1.004972 4.5 12.7 702435.4 dscfm 1.004638 4.5 12.9 698229.7 dscfm 1.004638 4.4 13.1 723863.1 dscfm 1.004638 5.4 11.8 665221.3 dscfm 1.005641 4 13.2 678402.2 dscfm 1.005641 4.2 12.8 685005.6 dscfm 1.005641 4.2 13 732193.9 dscfm 1.004972 4.6 13.2 758644.9 dscfm 1.004972 4.6 12.6 776474.9 dscfm 1.004972 4.2 13 688654.5 dscfm 1.004638 4.2 13.1 645270.7 dscfm 1.004638 4.2 13.2 735457.1 dscfm 1.004638 4.6 12.6

Page 71sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value 1.000628 17 18411 1.000628 17 18411 1.000628 17 18411 1.008315 17 18200 1.008315 17 18200 1.008315 17 18200 1.007312 17 18095 1.007312 17 18095 1.007312 17 18095 1.000628 17 18411 1.000294 17 18411 1.000294 17 18411 1.000628 17 18200 1.000294 17 18200 1.000294 17 18200 1.007312 17 18095 1.007312 17 18095 1.007312 17 18095 0.997954 17 18350 0.997954 17 18350 0.997954 17 18350 1.005641 17 18142 1.005641 17 18142 1.005641 17 18142 0.997286 17 18350 0.997286 17 18350 0.997286 17 18350 1.005641 17 18142 1.005641 17 18142 1.005641 17 18142 1.00798 17 18112 1.00798 17 18112 1.00798 17 18112 1.006978 17 18261 1.007312 17 18261 1.007312 17 18261 1.006309 17 18058.5 1.006309 17 18058.5 1.006309 17 18058.5 1.007646 17 18112 1.00798 17 18112 1.007312 17 18112 1.006978 17 18261 1.007312 17 18261 1.006644 17 18261 1.006309 17 18058 1.006309 17 18058 1.006309 17 18058

Page 72sampling_runs

fuel_sulfur 1.2487 1.2487 1.2487 1.23 1.23 1.23 1.35 1.35 1.35 1.2487 1.2487 1.2487 1.23 1.23 1.23 1.35 1.35 1.35 1.3749 1.3749 1.3749 1.2 1.2 1.2 1.3749 1.3749 1.3749 1.2 1.2 1.2 1.23 1.23 1.23 1.13 1.13 1.13 1.33 1.33 1.33 1.23 1.23 1.23 1.13 1.13 1.13 1.33 1.33 1.33

Page 73sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_name conc conc_units conc_ND conc_MDL 55318 IR1-PM-SS-2005

CS-1 1 PM (Filterable) 0.0209 FALSE 55318 IR1-PM-SS-2005

CS-1 2 PM (Filterable) 0.0205 FALSE 55318 IR1-PM-SS-2005

CS-1 3 PM (Filterable) 0.0227 FALSE 55318 IR1-PM-SB-2005

CS-1 1 PM (Filterable) 0.059 FALSE 55318 IR1-PM-SB-2005

CS-1 2 PM (Filterable) 0.064 FALSE 55318 IR1-PM-SB-2005

CS-1 3 PM (Filterable) 0.0291 FALSE 55318 IR1-PM-SS-2006

CS-1 1 PM (Filterable) 0.0285 FALSE 55318 IR1-PM-SS-2006

CS-1 2 PM (Filterable) 0.0492 FALSE 55318 IR1-PM-SS-2006

CS-1 3 PM (Filterable) 0.0569 FALSE 55318 IR1-PM-SB-2006

CS-1 1 PM (Filterable) 0.103 FALSE 55318 IR1-PM-SB-2006

CS-1 2 PM (Filterable) 0.1042 FALSE 55318 IR1-PM-SB-2006

CS-1 3 PM (Filterable) 0.0964 FALSE 55318 IR1-PM-SS-2007

CS-1 1 PM (Filterable) 0.0251 FALSE 55318 IR1-PM-SS-2007

CS-1 2 PM (Filterable) 0.0137 FALSE 55318 IR1-PM-SS-2007

CS-1 3 PM (Filterable) 0.0114 FALSE 55318 IR1-PM-SB-2007

CS-1 1 PM (Filterable) 0.0242 FALSE 55318 IR1-PM-SB-2007

CS-1 2 PM (Filterable) 0.1096 FALSE 55318 IR1-PM-SB-2007

CS-1 3 PM (Filterable) 0.014 FALSE 55318 IR2-PM-SS-2005

CS-1 1 PM (Filterable) 0.0403 FALSE 55318 IR2-PM-SS-2005

CS-1 2 PM (Filterable) 0.0314 FALSE 55318 IR2-PM-SS-2005

CS-1 3 PM (Filterable) 0.0409 FALSE 55318 IR2-PM-SB-2005

CS-1 1 PM (Filterable) 0.0934 FALSE 55318 IR2-PM-SB-2005

CS-1 2 PM (Filterable) 0.06284 FALSE 55318 IR2-PM-SB-2005

CS-1 3 PM (Filterable) 0.0417 FALSE 55318 IR2-PM-SS-2007

CS-1 1 PM (Filterable) 0.0334 FALSE 55318 IR2-PM-SS-2007

CS-1 2 PM (Filterable) 0.0179 FALSE 55318 IR2-PM-SS-2007

CS-1 3 PM (Filterable) 0.0272 FALSE 55318 IR2-PM-SB-2007

CS-1 1 PM (Filterable) 0.0567 FALSE 55318 IR2-PM-SB-2007

CS-1 2 PM (Filterable) 0.0386 FALSE 55318 IR2-PM-SB-2007

CS-1 3 PM (Filterable) 0.0358 FALSE 55318 IR3-PM-SS-2005

S3 1 PM (Filterable) 0.0225 FALSE 55318 IR3-PM-SS-2005

S3 2 PM (Filterable) 0.0231 FALSE 55318 IR3-PM-SS-2005

S3 3 PM (Filterable) 0.0196 FALSE 55318 IR3-PM-SB-2005

S3 1 PM (Filterable) 0.0434 FALSE 55318 IR3-PM-SB-2005

S3 2 PM (Filterable) 0.086 FALSE 55318 IR3-PM-SB-2005

S3 3 PM (Filterable) 0.1109 FALSE 55318 IR3-PM-SS-2006

S3 1 PM (Filterable) 0.0215 FALSE 55318 IR3-PM-SS-2006

S3 2 PM (Filterable) 0.0208 FALSE 55318 IR3-PM-SS-2006

S3 3 PM (Filterable) 0.0226 FALSE 55318 IR3-PM-SB-2006

S3 1 PM (Filterable) 0.0249 FALSE 55318 IR3-PM-SB-2006

S3 2 PM (Filterable) 0.0365 FALSE 55318 IR3-PM-SB-2006

S3 3 PM (Filterable) 0.0237 FALSE 55318 IR3-PM-SS-2007

S3 1 PM (Filterable) 0.0357 FALSE 55318 IR3-PM-SS-2007

S3 2 PM (Filterable) 0.0273 FALSE 55318 IR3-PM-SS-2007

S3 3 PM (Filterable) 0.0298 FALSE 55318 IR3-PM-SB-2007

S3 1 PM (Filterable) 0.0403 FALSE 55318 IR3-PM-SB-2007

S3 2 PM (Filterable) 0.0489 FALSE 55318 IR3-PM-SB-2007

S3 3 PM (Filterable) 0.0451 FALSE

Page 74sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment FALSE 0.04 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.038 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.041 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.112 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.121 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.054 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.054 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.093 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.108 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.192 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.199 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.178 pound per million British Thermal Unit (lb/MMBtu) FALSE 43.39 pound per hour (lb/hr)

FALSE 0.0471 pound per million British Thermal Unit (lb/MMBtu) FALSE 24.48 pound per hour (lb/hr)

FALSE 0.0262 pound per million British Thermal Unit (lb/MMBtu) FALSE 20.51 pound per hour (lb/hr)

FALSE 0.0216 pound per million British Thermal Unit (lb/MMBtu) FALSE 38 pound per hour (lb/hr)

FALSE 0.0457 pound per million British Thermal Unit (lb/MMBtu) FALSE 191.77 pound per hour (lb/hr)

FALSE 0.2073 pound per million British Thermal Unit (lb/MMBtu) FALSE 25.22 pound per hour (lb/hr)

FALSE 0.0265 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.079 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.061 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.078 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.182 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.12 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.08 pound per million British Thermal Unit (lb/MMBtu) FALSE 114.2 pound per hour (lb/hr)

FALSE 0.0619 pound per million British Thermal Unit (lb/MMBtu) FALSE 62.49 pound per hour (lb/hr)

FALSE 0.0334 pound per million British Thermal Unit (lb/MMBtu) FALSE 87.31 pound per hour (lb/hr)

FALSE 0.0512 pound per million British Thermal Unit (lb/MMBtu) FALSE 195.58 pound per hour (lb/hr)

FALSE 0.105 pound per million British Thermal Unit (lb/MMBtu) FALSE 133.27 pound per hour (lb/hr)

FALSE 0.0715 pound per million British Thermal Unit (lb/MMBtu) FALSE 127.14 pound per hour (lb/hr)

FALSE 0.0669 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.036 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.038 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.032 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.07 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.14 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.182 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.036 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.035 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.037 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.042 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.062 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.04 pound per million British Thermal Unit (lb/MMBtu) FALSE 210.99 pound per hour (lb/hr)

FALSE 0.0588 pound per million British Thermal Unit (lb/MMBtu) FALSE 150.98 pound per hour (lb/hr)

FALSE 0.0449 pound per million British Thermal Unit (lb/MMBtu) FALSE 187.76 pound per hour (lb/hr)

FALSE 0.0501 pound per million British Thermal Unit (lb/MMBtu) FALSE 242.59 pound per hour (lb/hr)

FALSE 0.0674 pound per million British Thermal Unit (lb/MMBtu) FALSE 292.67 pound per hour (lb/hr)

FALSE 0.0813 pound per million British Thermal Unit (lb/MMBtu) FALSE 279.59 pound per hour (lb/hr)

FALSE 0.0798 pound per million British Thermal Unit (lb/MMBtu) FALSE

Page 75sampling_run_pollutants1

run_pollutant_comment

Page 76sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL

Page 77sampling_run_fuel

fuel_conc_MDL

Page 78