### Name: Stephen Ward

Title: Senior Environmental Scientist Company: Hawaiian Electric Company, Inc. Sign Date: Name: Tony Wong Title: President Company:AirKinetics Inc. Sign Date: 8/30/2010 Permitted Facility Representative / Date Testing Company Representative / Date 

## Emissions Testing Unit 1 Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Thursday, February 10, 2011 Page 1 of 31

### Emissions Testing Unit 1

Facility Information: HI, Kahe 92-200 Farrington Hwy

Kapolei HI96707 Contact:Stephen Ward Phone:(808) 543-4535 Fax: (808) 543-4511 Email: stephen.ward@heco.com Testing Company:
AirKinetics Inc. 1308 S. Allec

Anaheim CA92805 Contact:Tony Wong Phone:(714) 245-1945 Fax: (714) 956-2350 Email:wongt@airkineticsinc.com

Air Permit Number: 0240-01-C Permitted Source ID/Name: 1 Permitted Maximum Process Rate: 903 MMBtu/hr Max. Normal Operation Process Rate: 818 MMBtu/hr Target Process Test Rate 806 MMBtu/hr

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Electrical power generation though combustion of fossil fuels (SIC Code 4911) is the only product or process Industry/SCC/NAIS221112

Sampling Location Information:

Test Parameter Information: AFS #:1500300501 FRS #:110000486439

SCC / Description10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: Normal Firing

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width stack 128.25 2793 348 2 128.25 12 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments LocationCarbon Monoxide Method 10 3 120 0 stack 2,3,7,8-TCDD Method 23 3 480 0 stack 1,2,3,7,8-PeCDD Method 23 3 480 0 stack 1,2,3,4,7,8-HxCDD Method 23 3 480 0 stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0 stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0 stack Regulation Description Compound Limit Unit



### Thursday, February 10, 2011 Page 2 of 31

### Emissions Testing Unit 1

1,2,3,4,6,7,8-HpCDD Method 23 3 480 0 stack OCDD Method 23 3 480 0 stack 2,3,7,8-TCDF Method 23 3 480 0 stack 1,2,3,7,8-PeCDF Method 23 3 480 0 stack 2,3,4,7,8-PeCDF Method 23 3 480 0 stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0 stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0 stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0 stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0 stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0 stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0 stack OCDF Method 23 3 480 0 stack Other TCDD Method 23 3 480 0 stack Other PeCDD Method 23 3 480 0 stack Other HxCDD Method 23 3 480 0 stack Other HpCDD Method 23 3 480 0 stack Other TCDF Method 23 3 480 0 stack Other PeCDF Method 23 3 480 0 stack Other HxCDF Method 23 3 480 0 stack Other HpCDF Method 23 3 480 0 stack Total Dioxins Method 23 3 480 0 stack Total Furans Method 23 3 480 0 stack 3,3',4,4'-TCB (PCB77) Method 23 3 480 0 stack 3,4,4',5-TCB (PCB81) Method 23 3 480 0 stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0 stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0 stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0 stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0 stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0 stack 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 480 0 stack
2,3',4,4',5,5'-HxCB (PCB167)Method 23 3 480 0 stack 3,3',4,4',5,5'-HxCB (PCB169)Method 23 3 480 0 stack 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 480 0 stack
Total TEQ Method 23 3 480 0 stack Total organic compounds

(TOC) as Propane Method 25A 3 120 0 stack
Hydrogen Chloride Method 26 3 60 0 stack Hydrogen Fluoride Method 26 3 60 0 stack Total Particulate OTM - 27/28 3 360 0 stack Filterable Particulate OTM - 27/28 3 360 0 stack Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 360 0 stack
Organic Condensible

Particulate OTM - 27/28 3 360 0 stack

Filterable PM2.5 OTM - 27/28 3 360 0 stack Total PM2.5 OTM - 27/28 3 360 0 stack Manganese Method 29 3 240 0 stack Antimony Method 29 3 240 0 stack Arsenic Method 29 3 240 0 stack Beryllium Method 29 3 240 0 stack Cadmium Method 29 3 240 0 stack


### Thursday, February 10, 2011 Page 3 of 31

### Emissions Testing Unit 1

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.
None Chromium Method 29 3 240 0 stack Lead Method 29 3 240 0 stack Nickel Method 29 3 240 0 stack Selenium Method 29 3 240 0 stack Cobalt Method 29 3 240 0 stack O2 Method 3A O2 3 120 0 stack Co2 Method 3A CO2 3 120 0 stack Filterable Particulate Method 5 3 240 0 stack Sulfur Dioxide Method 6C 3 120 0 stack Nitrogen oxides (NOx) Method 7E 3 120 0 stack



### Thursday, February 10, 2011 Page 4 of 31

### Emissions Testing Unit 1

Sampling / Stack Data Results Summary


### Locationstack - Method 10 Average Run Number 1 2 3 Test Date 6/13/2010 6/13/2010 6/13/2010 Run Start Time 8:17:00 AM 11:00:00 AM 1:35:00 PM

Run Finish Time 10:16:00 AM 12:59:00 PM 3:34:00 PM

Carbon Dioxide, % 11.72 11.63 11.53 11.627 Oxygen, % 6.13 5.94 6.04 6.037 Dry Volumetric Flow Rate, dry scfm 202438 205069 201385202,964.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.3 10.5 10.4 10.400 Fuel Type Oil Oil Oil Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Locationstack - Method 23 Average Run Number K1-M23-1 K1-M23-2 K1-M23-3 Test Date 6/7/2010 6/8/2010 6/10/2010 Run Start Time 9:05:00 AM 7:58:00 AM7:22:00 AM

Run Finish Time 5:37:00 PM4:25:00 PM 3:36:00 PM Net Run Time, minutes 480 480 480 Dry Gas Meter Volume Sampled, dscf 413.906 413.392 405.929 411.076 Moisture Content of Stack Gas, % 10.08 10.48 10.39 10.317 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 10.2 11.1 10.9 10.733 Oxygen, % 6.3 5.9 6.1 6.100 Average Stack Gas Temperature, °F 279.17 277.08 274.75 277.000 Dry Volumetric Flow Rate, dry scfm 212,341.8 209,473.6 206,581.2209,465.533 Actual Wet Volumetric Flue Gas Flow Rate, acfm 332,590.9 327,531.2 321,664.2327,262.100 Percent Isokinetic of Sampling Rate, % 98.8 100.0 100.4 99.733 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Thursday, February 10, 2011 Page 5 of 31

### Emissions Testing Unit 1

Locationstack - Method 25A Average Run Number 1 2 3 Test Date 6/13/2010 6/13/2010 6/13/2010 Run Start Time 8:17:00 AM 11:00:00 AM 1:35:00 PM

Run Finish Time 10:16:00 AM 12:59:00 PM 3:34:00 PM

Carbon Dioxide, % 11.72 11.63 11.53 11.627 Oxygen, % 6.13 5.94 6.04 6.037 Dry Volumetric Flow Rate, dry scfm 202438 205069 201385202,964.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.3 10.5 10.4 10.400 Fuel Type Oil Oil Oil Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Locationstack - Method 26 Average Run Number K1-M26-1 K1-M26-2 K1-M26-3 Test Date 6/10/2010 6/10/2010 6/10/2010 Run Start Time 7:41:00 AM 9:54:00 AM12:08:00 PM

Run Finish Time 8:41:00 AM 10:54:00 AM 1:08:00 PM

Net Run Time, minutes 60 60 60 Dry Gas Meter Volume Sampled, dscf 36.815 36.009 35.929 36.251 Moisture Content of Stack Gas, % 14.11 14.04 14.31 14.153 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 11.78 11.78 11.76 11.773 Oxygen, % 6.11 6.08 6.11 6.100 Average Stack Gas Temperature, °F 278.00 275.00 275.00 276.000 Dry Volumetric Flow Rate, dry scfm 195,154.1 195,679.4 195,197.0195,343.500 Actual Wet Volumetric Flue Gas Flow Rate, acfm 318,434.6 317,734.9 317,950.2318,039.900 Percent Isokinetic of Sampling Rate, % 102.2 99.6 99.7 100.500 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Thursday, February 10, 2011 Page 6 of 31

### Emissions Testing Unit 1

Locationstack - Method 29 Average Run Number K1-M5/29-1K1-M5/29- 2K1-M5/29-3

Test Date 6/9/2010 6/11/2010 6/11/2010 Run Start Time 1:22:00 PM 7:31:00 AM12:03:00 PM

Run Finish Time 5:34:00 PM 11:43:00 AM 4:12:00 PM

Net Run Time, minutes 240 240 240 Dry Gas Meter Volume Sampled, dscf 202.379 202.558 200.779 201.905 Moisture Content of Stack Gas, % 10.42 9.89 9.68 9.997 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 11 11 10.4 10.800 Oxygen, % 5.9 6.1 6.5 6.167 Average Stack Gas Temperature, °F 271.71 272.50 281.00 275.070 Dry Volumetric Flow Rate, dry scfm 205,045.1 206,489.0 206,427.2205,987.100 Actual Wet Volumetric Flue Gas Flow Rate, acfm 318,057.8 318,757.6 321,610.4319,475.267 Percent Isokinetic of Sampling Rate, % 100.1 99.5 99.4 99.667 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Thursday, February 10, 2011 Page 7 of 31

### Emissions Testing Unit 1

Locationstack - Method 5 Average Run Number K1-M5/29-1K1-M5/29- 2K1-M5/29-3

Test Date 6/9/2010 6/11/2010 6/11/2010 Run Start Time 1:22:00 PM 7:31:00 AM12:03:00 PM

Run Finish Time 5:34:00 PM 11:43:00 AM 4:12:00 PM

Net Run Time, minutes 240 240 240 Dry Gas Meter Volume Sampled, dscf 202.379 202.558 200.779 201.905 Moisture Content of Stack Gas, % 10.42 9.89 9.68 9.997 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 11 11 10.4 10.800 Oxygen, % 5.9 6.1 6.5 6.167 Average Stack Gas Temperature, °F 271.71 272.50 281.00 275.070 Dry Volumetric Flow Rate, dry scfm 205,045.1 206,489.0 206,427.2205,987.100 Actual Wet Volumetric Flue Gas Flow Rate, acfm 318,057.8 318,757.6 321,610.4319,475.267 Percent Isokinetic of Sampling Rate, % 100.1 99.5 99.4 99.667 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Locationstack - Method 6C Average Run Number 1 2 3 Test Date 6/10/2010 6/10/2010 6/10/2010 Run Start Time 7:41:00 AM 9:45:00 AM12:07:00 PM

Run Finish Time 9:40:00 AM 11:53:00 AM 2:06:00 PM

Carbon Dioxide, % 11.78 11.78 11.76 11.773 Oxygen, % 6.11 6.08 6.11 6.100 Dry Volumetric Flow Rate, dry scfm 209297 209297 209297209,297.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 9.9 9.9 9.9 9.900 Fuel Type Override Oil Oil Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Thursday, February 10, 2011 Page 8 of 31

### Emissions Testing Unit 1

Locationstack - Method 7E Average Run Number 1 2 3 Test Date 6/10/2010 6/10/2010 6/10/2010 Run Start Time 9:54:00 AM 9:54:00 AM12:07:00 PM

Run Finish Time 11:53:00 AM 11:53:00 AM 2:06:00 PM

Carbon Dioxide, % 11.78 11.78 11.76 11.773 Oxygen, % 6.08 6.08 6.11 6.090 Dry Volumetric Flow Rate, dry scfm 209297 209297 209297209,297.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 9.9 9.9 9.9 9.900 Fuel Type Oil Oil Oil Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Locationstack - OTM - 27/28 Average Run Number k1- otm27/28-1 K1-

OTM27/28 -2 K1- OTM27/28-3

Test Date 6/9/2010 6/10/2010 6/14/2010 Run Start Time 12:23:00 PM 8:19:00 AM7:23:00 AM

Run Finish Time 6:26:00 PM2:26:00 PM 1:35:00 PM Net Run Time, minutes 350.5372598355.843109 3363.8927146

Dry Gas Meter Volume Sampled, dscf 123.220 128.049 131.039 127.436 Moisture Content of Stack Gas, % 10.14 9.94 10.28 10.120 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 11 11.8 11 11.267 Oxygen, % 5.9 6.1 6 6.000 Average Stack Gas Temperature, °F 273.33 278.00 275.33 275.553 Dry Volumetric Flow Rate, dry scfm 208,114.3 209,333.0 211,321.5209,589.600 Actual Wet Volumetric Flue Gas Flow Rate, acfm 322,525.4 325,755.0 330,007.2326,095.867 Percent Isokinetic of Sampling Rate, % 96.1 97.8 97.0 96.967 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Thursday, February 10, 2011 Page 9 of 31

### Emissions Testing Unit 1

Emissions Summary


### Location: stack - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 lb/mmBtuO2 7.46E-04 8.67E-04 8.36E-04 0.001 ppm 7.89E-01 9.29E-01 8.90E-01 0.869 ppm@7%O2 7.43E-01 8.63E-01 8.33E-01 0.813



### Location: stack - Method 23 Compound: 1,2,3,4,6,7,8-HpCDD Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000437 0.0000000301 0.00000000921 0.000 lb/mmBtuO2 3.06E-12 2.06E-12 6.49E-13 0.000 ng/dscm 3.73E-03 2.57E-03 8.01E-04 0.002 ng/dscm@7%O2 3.55E-03 2.38E-03 7.52E-04 0.002 

### Compound: 1,2,3,4,6,7,8-HpCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000571 0.0000000125 0.0000000134 0.000 lb/mmBtuO2 4.00E-12 8.54E-13 9.44E-13 0.000 ng/dscm 4.87E-03 1.07E-03 1.17E-03 0.002 ng/dscm@7%O2 4.64E-03 9.92E-04 1.10E-03 0.002 

### Compound: 1,2,3,4,7,8,9-HpCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000124 0.00000000811 0.0000000049 0.000 lb/mmBtuO2 8.69E-13 5.54E-13 3.45E-13 0.000 ng/dscm 1.06E-03 6.93E-04 4.26E-04 0.001 ng/dscm@7%O2 1.01E-03 6.42E-04 4.00E-04 0.001 

### Compound: 1,2,3,4,7,8-HxCDD Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000213 0.0000000067 0.00000000843 0.000 lb/mmBtuO2 1.49E-12 4.58E-13 5.94E-13 0.000 ng/dscm 1.82E-03 5.72E-04 7.33E-04 0.001 ng/dscm@7%O2 1.73E-03 5.30E-04 6.88E-04 0.001 

### Compound: 1,2,3,4,7,8-HxCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000269 0.00000000657 0.0000000041 0.000 lb/mmBtuO2 1.88E-12 4.49E-13 2.89E-13 0.000 ng/dscm 2.30E-03 5.61E-04 3.57E-04 0.001 ng/dscm@7%O2 2.19E-03 5.20E-04 3.35E-04 0.001 

### Compound: 1,2,3,6,7,8-HxCDD Average


### Thursday, February 10, 2011 Page 10 of 31

### Emissions Testing Unit 1

RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000194 0.0000000112 0.00000000769 0.000 lb/mmBtuO2 1.36E-12 7.65E-13 5.42E-13 0.000 ng/dscm 1.66E-03 9.57E-04 6.69E-04 0.001 ng/dscm@7%O2 1.58E-03 8.87E-04 6.28E-04 0.001 

### Compound: 1,2,3,6,7,8-HxCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000277 0.00000000788 0.00000000532 0.000 lb/mmBtuO2 1.94E-12 5.38E-13 3.75E-13 0.000 ng/dscm 2.36E-03 6.73E-04 4.63E-04 0.001 ng/dscm@7%O2 2.25E-03 6.24E-04 4.35E-04 0.001 

### Compound: 1,2,3,7,8,9-HxCDD Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000184 0.0000000105 0.00000000726 0.000 lb/mmBtuO2 1.29E-12 7.17E-13 5.12E-13 0.000 ng/dscm 1.57E-03 8.97E-04 6.32E-04 0.001 ng/dscm@7%O2 1.49E-03 8.31E-04 5.94E-04 0.001 

### Compound: 1,2,3,7,8,9-HxCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.00000000812 0.00000000639 0.00000000166 0.000 lb/mmBtuO2 5.69E-13 4.36E-13 1.17E-13 0.000 ng/dscm 6.93E-04 5.46E-04 1.44E-04 0.000 ng/dscm@7%O2 6.60E-04 5.06E-04 1.35E-04 0.000 

### Compound: 1,2,3,7,8-PeCDD Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.00000000856 0.00000000889 0.0000000055 0.000 lb/mmBtuO2 6.00E-13 6.07E-13 3.88E-13 0.000 ng/dscm 7.30E-04 7.60E-04 4.79E-04 0.001 ng/dscm@7%O2 6.95E-04 7.04E-04 4.50E-04 0.001 

### Compound: 1,2,3,7,8-PeCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.000000025 0.00000000759 0.00000000513 0.000 lb/mmBtuO2 1.75E-12 5.18E-13 3.62E-13 0.000 ng/dscm 2.13E-03 6.48E-04 4.46E-04 0.001 ng/dscm@7%O2 2.03E-03 6.00E-04 4.19E-04 0.001 

### Compound: 2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.00000000301 0.0000001 0.0000001 0.000 lb/mmBtuO2 2.11E-13 6.83E-12 7.05E-12 0.000 ng/dscm 2.57E-04 8.54E-03 8.70E-03 0.006 ng/dscm@7%O2 2.45E-04 7.91E-03 8.17E-03 0.005



### Thursday, February 10, 2011 Page 11 of 31

### Emissions Testing Unit 1

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.00000004698 0.00000004709 0.00000002271 0.000 lb/mmBtuO2 3.29E-12 3.22E-12 1.60E-12 0.000 ng/dscm 4.01E-03 4.02E-03 1.98E-03 0.003 ng/dscm@7%O2 3.82E-03 3.73E-03 1.86E-03 0.003 

### Compound: 2,3,3',4,4'-PeCB (PCB105) Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.00000016 0.000000163 0.0000000784 0.000 lb/mmBtuO2 1.12E-11 1.11E-11 5.53E-12 0.000 ng/dscm 1.37E-02 1.39E-02 6.82E-03 0.011 ng/dscm@7%O2 1.30E-02 1.29E-02 6.41E-03 0.011 

### Compound: 2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000138 0.0000000168 0.00000000577 0.000 lb/mmBtuO2 9.67E-13 1.15E-12 4.07E-13 0.000 ng/dscm 1.18E-03 1.44E-03 5.02E-04 0.001 ng/dscm@7%O2 1.12E-03 1.33E-03 4.71E-04 0.001 

### Compound: 2,3,4,4',5-PeCB (PCB114) Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 7.01E-12 6.83E-12 7.05E-12 0.000 ng/dscm 8.53E-03 8.54E-03 8.70E-03 0.009 ng/dscm@7%O2 8.12E-03 7.91E-03 8.17E-03 0.008 

### Compound: 2,3',4,4',5-PeCB (PCB118) Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.000000404 0.0000004 0.000000175 0.000 lb/mmBtuO2 2.83E-11 2.73E-11 1.23E-11 0.000 ng/dscm 3.45E-02 3.42E-02 1.52E-02 0.028 ng/dscm@7%O2 3.28E-02 3.17E-02 1.43E-02 0.026 

### Compound: 2',3,4,4',5-PeCB (PCB123) Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 7.01E-12 6.83E-12 7.05E-12 0.000 ng/dscm 8.53E-03 8.54E-03 8.70E-03 0.009 ng/dscm@7%O2 8.12E-03 7.91E-03 8.17E-03 0.008 

### Compound: 2,3,4,6,7,8-HxCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000234 0.00000000425 0.000000004 0.000 lb/mmBtuO2 1.64E-12 2.90E-13 2.82E-13 0.000



### Thursday, February 10, 2011 Page 12 of 31

### Emissions Testing Unit 1

ng/dscm 2.00E-03 3.63E-04 3.48E-04 0.001 ng/dscm@7%O2 1.90E-03 3.36E-04 3.27E-04 0.001 

### Compound: 2,3,4,7,8-PeCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000309 0.000000007 0.00000000572 0.000 lb/mmBtuO2 2.17E-12 4.78E-13 4.03E-13 0.000 ng/dscm 2.64E-03 5.98E-04 4.98E-04 0.001 ng/dscm@7%O2 2.51E-03 5.54E-04 4.68E-04 0.001 

### Compound: 2,3,7,8-TCDD Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.00000000461 0.00000000568 0.00000000472 0.000 lb/mmBtuO2 3.23E-13 3.88E-13 3.33E-13 0.000 ng/dscm 3.93E-04 4.85E-04 4.11E-04 0.000 ng/dscm@7%O2 3.74E-04 4.49E-04 3.86E-04 0.000 

### Compound: 2,3,7,8-TCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000175 0.00000000715 0.00000000648 0.000 lb/mmBtuO2 1.23E-12 4.88E-13 4.57E-13 0.000 ng/dscm 1.49E-03 6.11E-04 5.64E-04 0.001 ng/dscm@7%O2 1.42E-03 5.66E-04 5.30E-04 0.001 

### Compound: 3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 7.01E-12 6.83E-12 7.05E-12 0.000 ng/dscm 8.53E-03 8.54E-03 8.70E-03 0.009 ng/dscm@7%O2 8.12E-03 7.91E-03 8.17E-03 0.008 

### Compound: 3,3',4,4',5-PeCB (PCB126) Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000001 0.0000001 0.0000001 0.000 lb/mmBtuO2 7.01E-12 6.83E-12 7.05E-12 0.000 ng/dscm 8.53E-03 8.54E-03 8.70E-03 0.009 ng/dscm@7%O2 8.12E-03 7.91E-03 8.17E-03 0.008 

### Compound: 3,3',4,4'-TCB (PCB77) Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000000653 0.0000000537 0.0000000221 0.000 lb/mmBtuO2 4.58E-15 3.67E-12 1.56E-12 0.000 ng/dscm 5.57E-06 4.59E-03 1.92E-03 0.002 ng/dscm@7%O2 5.30E-06 4.25E-03 1.80E-03 0.002 

### Compound: 3,4,4',5-TCB (PCB81) Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3


### Thursday, February 10, 2011 Page 13 of 31

### Emissions Testing Unit 1

Mass_mg 0.0000000102 0.0000001 0.0000001 0.000 lb/mmBtuO2 7.15E-13 6.83E-12 7.05E-12 0.000 ng/dscm 8.70E-04 8.54E-03 8.70E-03 0.006 ng/dscm@7%O2 8.28E-04 7.91E-03 8.17E-03 0.006 

### Compound: OCDD Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000827 0.000000101 0.0000000407 0.000 lb/mmBtuO2 5.79E-12 6.90E-12 2.87E-12 0.000 ng/dscm 7.06E-03 8.63E-03 3.54E-03 0.006 ng/dscm@7%O2 6.72E-03 8.00E-03 3.32E-03 0.006 

### Compound: OCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000253 0.00000000609 0.0000000109 0.000 lb/mmBtuO2 1.77E-12 4.16E-13 7.68E-13 0.000 ng/dscm 2.16E-03 5.20E-04 9.48E-04 0.001 ng/dscm@7%O2 2.06E-03 4.82E-04 8.90E-04 0.001 

### Compound: Other HpCDD Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000443 0 0 0.000 lb/mmBtuO2 3.10E-12 0.00E+00 0.00E+00 0.000 ng/dscm 3.78E-03 0.00E+00 0.00E+00 0.001 ng/dscm@7%O2 3.60E-03 0.00E+00 0.00E+00 0.001 

### Compound: Other HpCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000042 0 0 0.000 lb/mmBtuO2 2.94E-13 0.00E+00 0.00E+00 0.000 ng/dscm 3.58E-04 0.00E+00 0.00E+00 0.000 ng/dscm@7%O2 3.41E-04 0.00E+00 0.00E+00 0.000 

### Compound: Other HxCDD Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0 0.0000000077 0 0.000 lb/mmBtuO2 0.00E+00 5.26E-13 0.00E+00 0.000 ng/dscm 0.00E+00 6.58E-04 0.00E+00 0.000 ng/dscm@7%O2 0.00E+00 6.10E-04 0.00E+00 0.000 

### Compound: Other HxCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.00000006488 0 0 0.000 lb/mmBtuO2 4.55E-12 0.00E+00 0.00E+00 0.000 ng/dscm 5.54E-03 0.00E+00 0.00E+00 0.002 ng/dscm@7%O2 5.27E-03 0.00E+00 0.00E+00 0.002



### Thursday, February 10, 2011 Page 14 of 31

### Emissions Testing Unit 1

Compound: Other PeCDD Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.00000004974 0.00000000671 0 0.000 lb/mmBtuO2 3.49E-12 4.58E-13 0.00E+00 0.000 ng/dscm 4.24E-03 5.73E-04 0.00E+00 0.002 ng/dscm@7%O2 4.04E-03 5.31E-04 0.00E+00 0.002 

### Compound: Other PeCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000961 0.00000001441 0.00000000565 0.000 lb/mmBtuO2 6.73E-12 9.84E-13 3.98E-13 0.000 ng/dscm 8.20E-03 1.23E-03 4.92E-04 0.003 ng/dscm@7%O2 7.81E-03 1.14E-03 4.62E-04 0.003 

### Compound: Other TCDD Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.00000002129 0.0000000022 0 0.000 lb/mmBtuO2 1.49E-12 1.50E-13 0.00E+00 0.000 ng/dscm 1.82E-03 1.88E-04 0.00E+00 0.001 ng/dscm@7%O2 1.73E-03 1.74E-04 0.00E+00 0.001 

### Compound: Other TCDF Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000002215 0.00000001325 0.00000000822 0.000 lb/mmBtuO2 1.55E-11 9.05E-13 5.79E-13 0.000 ng/dscm 1.89E-02 1.13E-03 7.15E-04 0.007 ng/dscm@7%O2 1.80E-02 1.05E-03 6.72E-04 0.007 

### Compound: Total Dioxins Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.000000306 0.000000191 0.000000079 0.000 lb/mmBtuO2 2.14E-11 1.30E-11 5.57E-12 0.000 ng/dscm 2.61E-02 1.63E-02 6.87E-03 0.016 ng/dscm@7%O2 2.48E-02 1.51E-02 6.45E-03 0.015 

### Compound: Total Furans Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.000000641 0.000000089 0.00000007 0.000 lb/mmBtuO2 4.49E-11 6.08E-12 4.93E-12 0.000 ng/dscm 5.47E-02 7.60E-03 6.09E-03 0.023 ng/dscm@7%O2 5.21E-02 7.04E-03 5.72E-03 0.022 

### Compound: Total TEQ Average RunNumber K1-M23-1 K1-M23-2 K1-M23-3 Mass_mg 0.0000000431 0.00000002068 0.00000001541 0.000 lb/mmBtuO2 3.02E-12 1.41E-12 1.09E-12 0.000



### Thursday, February 10, 2011 Page 15 of 31

### Emissions Testing Unit 1

ng/dscm 3.68E-03 1.77E-03 1.34E-03 0.002 ng/dscm@7%O2 3.50E-03 1.64E-03 1.26E-03 0.002



### Location: stack - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 1.57E-03 1.57E-03 1.64E-03 0.002 ppm 1.05E+00 1.07E+00 1.11E+00 1.077 ppm@7%O2 9.88E-01 9.94E-01 1.04E+00 1.007



### Location: stack - Method 26 Compound: Hydrogen Chloride Average RunNumber K1-M26-1 K1-M26-2 K1-M26-3 Mass_mg 0.129 0.119 0.12 0.123 lb/mmBtuO2 1.00E-04 9.44E-05 9.56E-05 0.000 

### Compound: Hydrogen Fluoride Average RunNumber K1-M26-1 K1-M26-2 K1-M26-3 Mass_mg 0.213 0.217 0.205 0.212 lb/mmBtuO2 1.66E-04 1.72E-04 1.63E-04 0.000



### Location: stack - Method 29 Compound: Antimony Average RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3 Mass_mg 0.012362 0.011242 0.007562 0.010 lb/mmBtuO2 1.72E-06 1.59E-06 1.11E-06 0.000 

### Compound: Arsenic Average RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3 Mass_mg 0.0525 0.04712 0.031493 0.044 lb/mmBtuO2 7.32E-06 6.66E-06 4.61E-06 0.000 

### Compound: Beryllium Average RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3 Mass_mg 0.00093 0.00087 0.0007 0.001 lb/mmBtuO2 1.30E-07 1.23E-07 1.03E-07 0.000 

### Compound: Cadmium Average RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3 Mass_mg 0.000637 0.000399 0.001995 0.001 lb/mmBtuO2 8.89E-08 5.64E-08 2.92E-07 0.000 

### Compound: Chromium Average RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3



### Thursday, February 10, 2011 Page 16 of 31

### Emissions Testing Unit 1

Mass_mg 0.01642 0.01346 0.010602 0.013 lb/mmBtuO2 2.29E-06 1.90E-06 1.55E-06 0.000 

### Compound: Cobalt Average RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3 Mass_mg 0.326993 0.309154 0.236972 0.291 lb/mmBtuO2 4.56E-05 4.37E-05 3.47E-05 0.000 

### Compound: Lead Average RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3 Mass_mg 0.014628 0.013108 0.010032 0.013 lb/mmBtuO2 2.04E-06 1.85E-06 1.47E-06 0.000 

### Compound: Manganese Average RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3 Mass_mg 0.093699 0.077159 0.05092 0.074 lb/mmBtuO2 1.31E-05 1.09E-05 7.46E-06 0.000 

### Compound: Nickel Average RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3 Mass_mg 7.99984 7.75407 5.71992 7.158 lb/mmBtuO2 1.12E-03 1.10E-03 8.38E-04 0.001 

### Compound: Selenium Average RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3 Mass_mg 0.0071 0.0049 0.00457 0.006 lb/mmBtuO2 9.90E-07 6.92E-07 6.69E-07 0.000



### Location: stack - Method 5 Compound: Filterable Particulate Average RunNumber K1-M5/29-2 K1-M5/29-3 K1-M5/29-1 Mass_mg 279.4 190.5 362 277.300 lb/mmBtuO2 3.95E-02 2.79E-02 5.05E-02 0.039



### Location: stack - Method 6C Compound: Sulfur Dioxide Average Run 1 2 3 lb/mmBtuO2 3.99E-01 3.98E-01 3.98E-01 0.398 ppm 1.85E+02 1.85E+02 1.84E+02 184.667 ppm@7%O2 1.74E+02 1.74E+02 1.73E+02 173.667



### Location: stack - Method 7E Compound: Nitrogen oxides (NOx) Average Run 1 2 3



### Thursday, February 10, 2011 Page 17 of 31

### Emissions Testing Unit 1

Process Run Data lb/mmBtuO2 7.70E-01 7.70E-01 7.70E-01 0.770 ppm 4.98E+02 4.97E+02 4.97E+02 497.333 ppm@7%O2 4.67E+02 4.66E+02 4.67E+02 466.667



### Location: stack - OTM - 27/28 

### Compound: Filterable Particulate Average RunNumber k1-otm27/28-1 K1-OTM27/28-2 K1-OTM27/28-3 Mass_mg 236.8 191.9 190.4 206.367 lb/mmBtuO2 5.43E-02 4.29E-02 4.13E-02 0.046 

### Compound: Filterable PM2.5 Average RunNumber k1-otm27/28-1 K1-OTM27/28-2 K1-OTM27/28-3 Mass_mg 139.4 119.8 109.8 123.000 lb/mmBtuO2 3.19E-02 2.68E-02 2.38E-02 0.028 

### Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber k1-otm27/28-1 K1-OTM27/28-2 K1-OTM27/28-3 Mass_mg 24.1 23.4 27 24.833 lb/mmBtuO2 5.52E-03 5.23E-03 5.86E-03 0.006 

### Compound: Organic Condensible Particulate Average RunNumber k1-otm27/28-1 K1-OTM27/28-2 K1-OTM27/28-3 Mass_mg 13.5 4.2 9.3 9.000 lb/mmBtuO2 3.09E-03 9.38E-04 2.02E-03 0.002 

### Compound: Total Particulate Average RunNumber k1-otm27/28-1 K1-OTM27/28-2 K1-OTM27/28-3 Mass_mg 272.5 217.6 224.8 238.300 lb/mmBtuO2 6.24E-02 4.86E-02 4.88E-02 0.053 

### Compound: Total PM2.5 Average RunNumber k1-otm27/28-1 K1-OTM27/28-2 K1-OTM27/28-3 Mass_mg 175.1 145.5 144.2 154.933 lb/mmBtuO2 4.01E-02 3.25E-02 3.13E-02 0.035



### Thursday, February 10, 2011 Page 18 of 31

### Emissions Testing Unit 1

Process Run Data



### Run Name Value UOM Comments Target Value 1 0


### 2 0
1 0
2 0


### 1 0
2 0
1 0


### 2 0
1 0
2 0


### 1 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
2 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
1 0


### 1 Unit Gross Electric Generation 85.14 Mwe
1 Unit Net Electric Generation 81.41 MWh
1 Steam Output 611.41,000 lbs steam/hr


### 1 Average Heat Input 816.28MMBtu/hr EPA Method 23: K1-M23-1 1 Fuel Oil Firing Rate 43.03 Klb/hr June 7, 2010 Test Day 

### 3 0
3 0 

### 3 0 3 0
3 0 

### 3 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
3 0
3 Unit Gross Electric Generation 85.13 Mwe 

### 3 Unit Net Electric Generation 81.41 MWh
3 Steam Output 612.21,000 lbs steam/hr
3 Average Heat Input 818.63MMBtu/hr EPA Method 23: K1-M23-2 

### 3 Fuel Oil Firing Rate 43.13 Klb/hr June 8, 2010 Test Day 4 0



### Thursday, February 10, 2011 Page 19 of 31

### Emissions Testing Unit 1

4 0


### 4 0
4 0
4 0


### 4 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
4 0
4 Unit Gross Electric Generation 85 Mwe


### 4 Unit Net Electric Generation 81.39 MWh
4 Steam Output 611.51,000 lbs steam/hr EPA Method OTM 27/28: K1- OTM27/28-1 

### 4 Average Heat Input 807.92MMBtu/hr EPA Method 5/29: K1-M5/29-1 4 Fuel Oil Firing Rate 43.02 Klb/hr June 9, 2010 Test Day 

### 5 0 5 0 

### 5 0 5 0 5 0 

### 5 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
5 0 5 Unit Gross Electric Generation 85.27 Mwe EPA Method OTM 27/28: K1- OTM27/28-2 5 Unit Net Electric Generation 81.57 MWh EPA Method 26/CTM-033: K1- M26-1, K1-M26- 2, K1-M26-3 5 Steam Output 612.71,000 lbs steam/hr EPA Method 23: K1-M23-3 

### 5 Average Heat Input 824.99MMBtu/hr EPA Method 3A, 6C, and 7E: Run 1, Run 2, Run 3 5 Fuel Oil Firing Rate 43.28 Klb/hr June 10, 2010 Test Day 

### 6 0
6 0


### 6 0
6 0
6 0



### Thursday, February 10, 2011 Page 20 of 31

### Emissions Testing Unit 1

6 Residual Oil (No. 6) Burned 0 1000 Gallons/hr


### 6 0
6 Unit Gross Electric Generation 85.12 Mwe
6 Unit Net Electric Generation 81.43 MWh


### 6 Steam Output 6121,000 lbs steam/hr EPA Method 30B: K1-M30B-1, K1- M30B-2 6 Average Heat Input 810.62MMBtu/hr EPA Method 5/29: K1-M5/29-2, K1- M5/29-3 6 Fuel Oil Firing Rate 42.98 Klb/hr June 11, 2010 Test Day 

### 7 0
7 0
7 0


### 7 0
7 0
7 Residual Oil (No. 6) Burned 0 1000 Gallons/hr


### 7 0 EPA Method 0031/SW-846 8260B: K1- M0031-1, K1- M0031-2, K1- M0031-3 7 Unit Gross Electric Generation 85.14 Mwe EPA Method 0010/SW-846 8270D: K1- M0010-1, K1- M0010-2, K1- M0010-3 

### 7 Unit Net Electric Generation 81.44 MWh EPA Method 316: K1-M316-1, K1- M316-2, K1- M316-3 7 Steam Output 611.81,000 lbs steam/hr EPA Method 10 and 25A: Run 1, Run 2, Run 3 7 Average Heat Input 813.92MMBtu/hr EPA Method 18: K1-M18-1, K1- M18-2, K1-M18-3 7 Fuel Oil Firing Rate 43 Klb/hr June 13, 2010 Test Day 

### 8 0
8 0 8 0



### Thursday, February 10, 2011 Page 21 of 31

### Emissions Testing Unit 1

APCD Run Data

Process Lab Run Data 8 0 

### 8 0
8 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
8 0 

### 8 Unit Gross Electric Generation 85.1 Mwe 8 Unit Net Electric Generation 81.42 MWh
8 Steam Output 6131,000 lbs steam/hr EPA Method OTM 27/28: K1- OTM27/28-3 8 Average Heat Input 844.42MMBtu/hr EPA Method 30B: K1-M30B-3 

### 8 Fuel Oil Firing Rate 43.28 Klb/hr June 14, 2010 Test Day

Run Name Value UOM Comments Target Value 1 None 0


### 1 0
1 0
1 0

Run Name ValueUOM Comments 

### 1 none 0 1 0 1 0 

### 1 0 1 0



### Thursday, February 10, 2011 Page 22 of 31

### Emissions Testing Unit 1

Sampling / Stack Data Results Detail


### Locationstack - Method 10 Average Run Number 1 2 3 Test Date 6/13/2010 6/13/2010 6/13/2010 Run Start Time 8:17:00 AM11:00:00 AM 1:35:00 PM Run Finish Time 10:16:00 AM12:59:00 PM 3:34:00 PM Carbon Dioxide, % 11.72 11.63 11.53 11.627 Oxygen, % 6.13 5.94 6.04 6.037 Fuel Factor 1.26 1.29 1.29 Dry Volumetric Flow Rate, dry scfm 202438 205069 201385202,964.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 10.3 10.5 10.4 10.400 Analyzer Make Thermo Electron Thermo

Electron Thermo

Electron Analyzer Model 48 48 48 48.000 Analyzer Serial Number Operating Range 0 0 0 0.000 Operating Units No. Readings/Avg. 0 0 0 0.000 Calibration Set 0 0 0 0.000 Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen Calibration Pre Zero Cylinder Instrument Response -0.13 -0.07 -0.24 -0.147 Calibration Pre Zero Cylinder Bias -0.66 -0.33 -1.27 -0.753 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID COCC149350- Diluted2 COCC149350- Diluted2 COCC149350- Diluted2 Calibration Pre High Cylinder Instrument Response 9.2 9.24 9.12 9.187 Calibration Pre High Cylinder Bias 0.33 0.55 -0.11 0.257 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen Calibration Post Zero Cylinder Instrument Response -0.07 -0.24 -0.41 -0.240 Calibration Post Zero Cylinder Bias -0.33 -1.27 -2.2 -1.267 Calibration Post Zero Cylinder Drift 0.33 0.94 0.93 0.733 Calibration Post High Cylinder ID COCC149350- Diluted2 COCC149350- Diluted2 COCC149350- Diluted2 Calibration Post High Cylinder Instrument Response 9.24 9.12 8.9 9.087 Calibration Post High Cylinder Bias 0.55 -0.11 -1.32 -0.293 Calibration Post High Cylinder Drift 0.22 0.66 1.21 0.697 Cavg 0.71 0.8 0.59 0.700 Cavg Units ppmvd ppmvd ppmvd Cgas 0.7891 0.9289 0.89 0.869 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000 Cgasw 0 0 0 0.000 Cgasw Units



### Thursday, February 10, 2011 Page 23 of 31

### Emissions Testing Unit 1

Locationstack - Method 23 Average Run Number K1-M23-1 K1-M23-2 K1-M23-3 Test Date 6/7/2010 6/8/2010 6/10/2010 Run Start Time 9:05:00 AM7:58:00 AM7:22:00 AM Run Finish Time 5:37:00 PM4:25:00 PM 3:36:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 480 480 480 Nozzle Diameter, inches 0.26 0.26 0.259 0.260 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 1.03 0.98 0.98 0.997 Barometric Pressure, inches of Mercury 29.8 29.9 29.9 29.867 Average Orifice Meter Differential, inches H2O 2.75 2.65 2.51 2.637 Dry Gas Meter Volume Sampled, cubic feet 439.534 456.971 448.329 448.278 Average Dry Gas Meter Temperature, °F 119.10 115.33 114.63 116.353 Dry Gas Meter Volume Sampled, dscf 413.906 413.392 405.929 411.076 Total Moisture Liquid collected, g 985.3 1028.5 999.61,004.467 Volume of Water Vapor, standard cubic feet 46.38 48.41 47.05 47.280 Moisture Content of Stack Gas, % 10.08 10.48 10.39 10.317 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8992 0.8952 0.8961 0.897 Carbon Dioxide, % 10.2 11.1 10.9 10.733 Oxygen, % 6.3 5.9 6.1 6.100 Carbon Monoxide & Nitrogen, % 83.5 83 83 83.167 Fuel Factor 1.43 1.35 1.36 Dry Molecular Weight, lb/lb-Mole 29.88 30.01 29.99 29.960 Wet Molecular weight, lb/lb-Mole 28.68 28.75 28.74 28.723 Flue Gas Static Pressure, inches of H2O -0.86 -0.88 -0.82 -0.853 Absolute Flue Gas Pressure, inches of Mercury 29.74 29.84 29.84 29.807 Average Stack Gas Temperature, °F 279.17 277.08 274.75 277.000 Average Velocity Head, inches of H2O 0.8542763969 83190.835729409

4384710.808369955

237497 0.833
Average Stack Gas Velocity, feet/second 61.79 60.85 59.76 60.800 Stack Cross-Sectional Area, square feet 89.710 89.710 89.710 89.710 Dry Volumetric Flow Rate, dry scfm 212,341.8 209,473.6 206,581.2209,465.533 Actual Wet Volumetric Flue Gas Flow Rate, acfm 332,590.9 327,531.2 321,664.2327,262.100 Percent Isokinetic of Sampling Rate, % 98.8 100.0 100.4 99.733 Percent Excess Air, % 40.0 36.8 38.6 38.467 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 128.25 128.25 128.25 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Thursday, February 10, 2011 Page 24 of 31

### Emissions Testing Unit 1

Locationstack - Method 25A Average Run Number 1 2 3 Test Date 6/13/2010 6/13/2010 6/13/2010 Run Start Time 8:17:00 AM11:00:00 AM 1:35:00 PM Run Finish Time 10:16:00 AM12:59:00 PM 3:34:00 PM Carbon Dioxide, % 11.72 11.63 11.53 11.627 Oxygen, % 6.13 5.94 6.04 6.037 Fuel Factor 1.26 1.29 1.29 Dry Volumetric Flow Rate, dry scfm 202438 205069 201385202,964.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 10.3 10.5 10.4 10.400 Analyzer Make Analyzer Model Analyzer Serial Number Operating Range 0 0 0 0.000 Operating Units No. Readings/Avg. 0 0 0 0.000 Calibration Set 1 1 1 1.000 Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen Calibration Pre Zero Cylinder Instrument Response 0.04 0.03 0.09 0.053 Calibration Pre Zero Cylinder Bias 0 -0.13 0.66 0.177 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID THC-CC163385- Diluted3 THC-CC163385- Diluted3 THC-CC163385- Diluted3 Calibration Pre High Cylinder Instrument Response 2.04 2.03 2.07 2.047 Calibration Pre High Cylinder Bias 0 -0.13 0.4 0.090 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen Calibration Post Zero Cylinder Instrument Response 0.03 0.09 0.08 0.067 Calibration Post Zero Cylinder Bias -0.13 0.66 0.53 0.353 Calibration Post Zero Cylinder Drift 0.13 0.79 0.13 0.350 Calibration Post High Cylinder ID THC-CC163385- Diluted3 THC-CC163385- Diluted3 THC-CC163385- Diluted3 Calibration Post High Cylinder Instrument Response 2.03 2.07 1.99 2.030 Calibration Post High Cylinder Bias -0.13 0.4 -0.66 -0.130 Calibration Post High Cylinder Drift 0.13 0.53 1.06 0.573 Cavg 0.97 1 1.04 1.003 Cavg Units ppmvw ppmvw ppmvw Cgas 1.0528 1.0661 1.1069 1.075 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000 Cgasw 0.944350.954170854 2713570.991825192

802057 0.963
Cgasw Units ppmvw ppmvw ppmvw



### Thursday, February 10, 2011 Page 25 of 31

### Emissions Testing Unit 1

Locationstack - Method 26 Average Run Number K1-M26-1 K1-M26-2 K1-M26-3 Test Date 6/10/2010 6/10/2010 6/10/2010 Run Start Time 7:41:00 AM9:54:00 AM12:08:00 PM Run Finish Time 8:41:00 AM10:54:00 AM 1:08:00 PM Net Traversing Points 12 12 12 Net Run Time, minutes 60 60 60 Nozzle Diameter, inches 0.225 0.225 0.225 0.225 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 1.03 1.03 1.03 1.030 Barometric Pressure, inches of Mercury 29.9 29.9 29.9 29.900 Average Orifice Meter Differential, inches H2O 1.30 1.30 1.30 1.300 Dry Gas Meter Volume Sampled, cubic feet 38.050 37.360 37.400 37.603 Average Dry Gas Meter Temperature, °F 103.50 105.67 107.54 105.570 Dry Gas Meter Volume Sampled, dscf 36.815 36.009 35.929 36.251 Total Moisture Liquid collected, g 128.6 125 127.5 127.033 Volume of Water Vapor, standard cubic feet 6.05 5.88 6.00 5.977 Moisture Content of Stack Gas, % 14.11 14.04 14.31 14.153 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8589 0.8596 0.8569 0.858 Carbon Dioxide, % 11.78 11.78 11.76 11.773 Oxygen, % 6.11 6.08 6.11 6.100 Carbon Monoxide & Nitrogen, % 82.11 82.14 82.13 82.127 Fuel Factor 1.26 1.26 1.26 Dry Molecular Weight, lb/lb-Mole 30.13 30.13 30.13 30.130 Wet Molecular weight, lb/lb-Mole 28.42 28.43 28.39 28.413 Flue Gas Static Pressure, inches of H2O -0.82 -0.82 -0.82 -0.820 Absolute Flue Gas Pressure, inches of Mercury 29.84 29.84 29.84 29.840 Average Stack Gas Temperature, °F 278.00 275.00 275.00 276.000 Average Velocity Head, inches of H2O 0.78 0.78 0.78 0.780 Average Stack Gas Velocity, feet/second 59.16 59.03 59.07 59.087 Stack Cross-Sectional Area, square feet 89.710 89.710 89.710 89.710 Dry Volumetric Flow Rate, dry scfm 195,154.1 195,679.4 195,197.0195,343.500 Actual Wet Volumetric Flue Gas Flow Rate, acfm 318,434.6 317,734.9 317,950.2318,039.900 Percent Isokinetic of Sampling Rate, % 102.2 99.6 99.7 100.500 Percent Excess Air, % 39.2 39.0 39.2 39.133 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 128.25 128.25 128.25 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Thursday, February 10, 2011 Page 26 of 31

### Emissions Testing Unit 1

Locationstack - Method 29 Average Run Number K1-M5/29-1K1-M5/29-2K1-M5/29-3 Test Date 6/9/2010 6/11/2010 6/11/2010 Run Start Time 1:22:00 PM7:31:00 AM12:03:00 PM Run Finish Time 5:34:00 PM11:43:00 AM 4:12:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 240 240 240 Nozzle Diameter, inches 0.26 0.26 0.259 0.260 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.98 1.03 1.03 1.013 Barometric Pressure, inches of Mercury 29.9 29.9 29.9 29.900 Average Orifice Meter Differential, inches H2O 2.50 2.55 2.53 2.527 Dry Gas Meter Volume Sampled, cubic feet 224.453 212.438 213.245 216.712 Average Dry Gas Meter Temperature, °F 117.02 113.56 120.81 117.130 Dry Gas Meter Volume Sampled, dscf 202.379 202.558 200.779 201.905 Total Moisture Liquid collected, g 500.1 472.3 457 476.467 Volume of Water Vapor, standard cubic feet 23.54 22.23 21.51 22.427 Moisture Content of Stack Gas, % 10.42 9.89 9.68 9.997 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8958 0.9011 0.9032 0.900 Carbon Dioxide, % 11 11 10.4 10.800 Oxygen, % 5.9 6.1 6.5 6.167 Carbon Monoxide & Nitrogen, % 83.1 82.9 83.1 83.033 Fuel Factor 1.36 1.35 1.38 Dry Molecular Weight, lb/lb-Mole 30.00 30.00 29.92 29.973 Wet Molecular weight, lb/lb-Mole 28.75 28.81 28.77 28.777 Flue Gas Static Pressure, inches of H2O -0.84 -0.83 -0.83 -0.833 Absolute Flue Gas Pressure, inches of Mercury 29.84 29.84 29.84 29.840 Average Stack Gas Temperature, °F 271.71 272.50 281.00 275.070 Average Velocity Head, inches of H2O 0.7937439071 148270.798188533

2915310.802086545

763319 0.798
Average Stack Gas Velocity, feet/second 59.09 59.22 59.75 59.353 Stack Cross-Sectional Area, square feet 89.710 89.710 89.710 89.710 Dry Volumetric Flow Rate, dry scfm 205,045.1 206,489.0 206,427.2205,987.100 Actual Wet Volumetric Flue Gas Flow Rate, acfm 318,057.8 318,757.6 321,610.4319,475.267 Percent Isokinetic of Sampling Rate, % 100.1 99.5 99.4 99.667 Percent Excess Air, % 36.8 38.6 42.1 39.167 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 128.25 128.25 128.25 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Thursday, February 10, 2011 Page 27 of 31

### Emissions Testing Unit 1

Locationstack - Method 5 Average Run Number K1-M5/29-1K1-M5/29-2K1-M5/29-3 Test Date 6/9/2010 6/11/2010 6/11/2010 Run Start Time 1:22:00 PM7:31:00 AM12:03:00 PM Run Finish Time 5:34:00 PM11:43:00 AM 4:12:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 240 240 240 Nozzle Diameter, inches 0.26 0.26 0.259 0.260 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.98 1.03 1.03 1.013 Barometric Pressure, inches of Mercury 29.9 29.9 29.9 29.900 Average Orifice Meter Differential, inches H2O 2.50 2.55 2.53 2.527 Dry Gas Meter Volume Sampled, cubic feet 224.453 212.438 213.245 216.712 Average Dry Gas Meter Temperature, °F 117.02 113.56 120.81 117.130 Dry Gas Meter Volume Sampled, dscf 202.379 202.558 200.779 201.905 Total Moisture Liquid collected, g 500.1 472.3 457 476.467 Volume of Water Vapor, standard cubic feet 23.54 22.23 21.51 22.427 Moisture Content of Stack Gas, % 10.42 9.89 9.68 9.997 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8958 0.9011 0.9032 0.900 Carbon Dioxide, % 11 11 10.4 10.800 Oxygen, % 5.9 6.1 6.5 6.167 Carbon Monoxide & Nitrogen, % 83.1 82.9 83.1 83.033 Fuel Factor 1.36 1.35 1.38 Dry Molecular Weight, lb/lb-Mole 30.00 30.00 29.92 29.973 Wet Molecular weight, lb/lb-Mole 28.75 28.81 28.77 28.777 Flue Gas Static Pressure, inches of H2O -0.84 -0.83 -0.83 -0.833 Absolute Flue Gas Pressure, inches of Mercury 29.84 29.84 29.84 29.840 Average Stack Gas Temperature, °F 271.71 272.50 281.00 275.070 Average Velocity Head, inches of H2O 0.7937439071 148270.798188533

2915310.802086545

763319 0.798
Average Stack Gas Velocity, feet/second 59.09 59.22 59.75 59.353 Stack Cross-Sectional Area, square feet 89.710 89.710 89.710 89.710 Dry Volumetric Flow Rate, dry scfm 205,045.1 206,489.0 206,427.2205,987.100 Actual Wet Volumetric Flue Gas Flow Rate, acfm 318,057.8 318,757.6 321,610.4319,475.267 Percent Isokinetic of Sampling Rate, % 100.1 99.5 99.4 99.667 Percent Excess Air, % 36.8 38.6 42.1 39.167 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 128.25 128.25 128.25 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Thursday, February 10, 2011 Page 28 of 31

### Emissions Testing Unit 1

Locationstack - Method 6C Average Run Number 1 2 3 Test Date 6/10/2010 6/10/2010 6/10/2010 Run Start Time 7:41:00 AM9:45:00 AM12:07:00 PM Run Finish Time 9:40:00 AM11:53:00 AM 2:06:00 PM Carbon Dioxide, % 11.78 11.78 11.76 11.773 Oxygen, % 6.11 6.08 6.11 6.100 Fuel Factor 1.26 1.26 1.26 Dry Volumetric Flow Rate, dry scfm 209297 209297 209297209,297.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 9.9 9.9 9.9 9.900 Analyzer Make Analyzer Model Analyzer Serial Number Operating Range 0 0 0 0.000 Operating Units No. Readings/Avg. 0 0 0 0.000 Calibration Set 3 3 3 3.000 Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen Calibration Pre Zero Cylinder Instrument Response 0 1.67 1 0.890 Calibration Pre Zero Cylinder Bias 0 0.18 0.11 0.097 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID SO2-CC102092- Diluted1 SO2-CC102092- Diluted1 SO2-CC102092- Diluted1 Calibration Pre High Cylinder Instrument Response 443.67 444.33 444.5 444.167 Calibration Pre High Cylinder Bias -1.54 -1.47 -1.45 -1.487 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen Calibration Post Zero Cylinder Instrument Response 1.67 1 0.67 1.113 Calibration Post Zero Cylinder Bias 0.18 0.11 0.07 0.120 Calibration Post Zero Cylinder Drift 0.18 0.07 0.04 0.097 Calibration Post High Cylinder ID SO2-CC102092- Diluted1 SO2-CC102092- Diluted1 SO2-CC102092- Diluted1 Calibration Post High Cylinder Instrument Response 444.33 444.5 444.67 444.500 Calibration Post High Cylinder Bias -1.47 -1.45 -1.43 -1.450 Calibration Post High Cylinder Drift 7.0000000000 0001E-02 0.02 0.02 0.037
Cavg 179.33 179.54 179.09 179.320 Cavg Units ppmvd ppmvd ppmvd Cgas 184.8729 184.608 184.3809 184.621 Cgas Units ppmvd ppmvd ppmvd Fuel Type Override Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000 Cgasw 0 0 0 0.000 Cgasw Units



### Thursday, February 10, 2011 Page 29 of 31

### Emissions Testing Unit 1

Locationstack - Method 7E Average Run Number 1 2 3 Test Date 6/10/2010 6/10/2010 6/10/2010 Run Start Time 9:54:00 AM9:54:00 AM12:07:00 PM Run Finish Time 11:53:00 AM11:53:00 AM 2:06:00 PM Carbon Dioxide, % 11.78 11.78 11.76 11.773 Oxygen, % 6.08 6.08 6.11 6.090 Fuel Factor 1.26 1.26 1.26 Dry Volumetric Flow Rate, dry scfm 209297 209297 209297209,297.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 9.9 9.9 9.9 9.900 Analyzer Make CAI ModelCAI Model CAI Model Analyzer Model 600 600 600 600.000 Analyzer Serial Number Operating Range 0 0 0 0.000 Operating Units No. Readings/Avg. 0 0 0 0.000 Calibration Set 4 4 4 4.000 Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen Calibration Pre Zero Cylinder Instrument Response 0 0.72 0.73 0.483 Calibration Pre Zero Cylinder Bias 0 0.08 0.08 0.053 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID NOx-CC187760- Diluted1 NOx-CC187760- Diluted1 NOx-CC187760- Diluted1 Calibration Pre High Cylinder Instrument Response 445.3 445.02 445.08 445.133 Calibration Pre High Cylinder Bias -1.56 -1.59 -1.59 -1.580 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen Calibration Post Zero Cylinder Instrument Response 0.72 0.73 0.74 0.730 Calibration Post Zero Cylinder Bias 0.08 0.08 0.08 0.080 Calibration Post Zero Cylinder Drift 0.08 0 0 0.027 Calibration Post High Cylinder ID NOx-CC187760- Diluted1 NOx-CC187760- Diluted1 NOx-CC187760- Diluted1 Calibration Post High Cylinder Instrument Response 445.02 445.08 444.03 444.710 Calibration Post High Cylinder Bias -1.59 -1.59 -1.7 -1.627 Calibration Post High Cylinder Drift 0.03 0 0.11 0.047 Cavg 483.53 483.2 482.2 482.977 Cavg Units ppmvd ppmvd ppmvd Cgas 497.5087 497.3241 496.8478 497.227 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000 Cgasw 0 0 0 0.000 Cgasw Units



### Thursday, February 10, 2011 Page 30 of 31

### Emissions Testing Unit 1

Locationstack - OTM - 27/28 Average Run Number k1-otm27/28-1 K1- OTM27/28-2 K1-

OTM27/28-3 Test Date 6/9/2010 6/10/2010 6/14/2010 Run Start Time 12:23:00 PM8:19:00 AM7:23:00 AM Run Finish Time 6:26:00 PM2:26:00 PM 1:35:00 PM Net Traversing Points 12 12 12 Net Run Time, minutes 350.5372598355.8431093363.8927146 Nozzle Diameter, inches 0.17 0.17 0.17 0.170 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 1 1 1.03 1.010 Barometric Pressure, inches of Mercury 29.9 29.9 29.8 29.867 Average Orifice Meter Differential, inches H2O 0.44 0.48 0.45 0.457 Dry Gas Meter Volume Sampled, cubic feet 133.841 138.448 137.087 136.459 Average Dry Gas Meter Temperature, °F 113.75 111.17 107.29 110.737 Dry Gas Meter Volume Sampled, dscf 123.220 128.049 131.039 127.436 Total Moisture Liquid collected, g 295.4 300.3 319 304.900 Volume of Water Vapor, standard cubic feet 13.90 14.14 15.02 14.353 Moisture Content of Stack Gas, % 10.14 9.94 10.28 10.120 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8986 0.9006 0.8972 0.899 Carbon Dioxide, % 11 11.8 11 11.267 Oxygen, % 5.9 6.1 6 6.000 Carbon Monoxide & Nitrogen, % 83.1 82.1 83 82.733 Fuel Factor 1.36 1.25 1.35 Dry Molecular Weight, lb/lb-Mole 30.00 30.13 30.00 30.043 Wet Molecular weight, lb/lb-Mole 28.78 28.92 28.77 28.823 Flue Gas Static Pressure, inches of H2O -0.84 -0.82 -0.84 -0.833 Absolute Flue Gas Pressure, inches of Mercury 29.84 29.84 29.74 29.807 Average Stack Gas Temperature, °F 273.33 278.00 275.33 275.553 Average Velocity Head, inches of H2O 0.8153833227 390220.830483569

9669020.848046785

736507 0.831
Average Stack Gas Velocity, feet/second 59.92 60.52 61.31 60.583 Stack Cross-Sectional Area, square feet 89.710 89.710 89.710 89.710 Dry Volumetric Flow Rate, dry scfm 208,114.3 209,333.0 211,321.5209,589.600 Actual Wet Volumetric Flue Gas Flow Rate, acfm 322,525.4 325,755.0 330,007.2326,095.867 Percent Isokinetic of Sampling Rate, % 96.1 97.8 97.0 96.967 Percent Excess Air, % 36.8 39.2 37.7 37.900 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 128.25 128.25 128.25 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Thursday, February 10, 2011 Page 31 of 31