Name: Stephen Ward

Title: Senior Environmental Scientist

Company: Hawaiian Electric Company, Inc.

Sign Date:

Name: Tony Wong

Title: President

Company: AirKinetics Inc.

Sign Date: 8/30/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Emissions Testing Unit 1

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 10, 2011 Page 1 of 31
Emissions Testing Unit 1

Facility Information:

HI, Kahe

92-200 Farrington Hwy

Kapolei HI 96707

Contact: Stephen Ward

Phone: (808) 543-4535

Fax: (808) 543-4511

Email: stephen.ward@heco.com

Testing Company:

AirKinetics Inc.

1308 S. Allec

Anaheim CA 92805

Contact:Tony Wong

Phone: (714) 245-1945

Fax: (714) 956-2350

Email: wongt@airkineticsinc.com

Air Permit Number:

0240-01-C

Permitted Source ID/Name:

1

Permitted Maximum Process Rate:

903 MMBtu/hr

Max. Normal Operation Process Rate:

818 MMBtu/hr

Target Process Test Rate

806 MMBtu/hr

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Electrical power generation though combustion of fossil fuels (SIC Code 4911) is the only product or process

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 1500300501 FRS #: 110000486439

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

stack 128.25 0 0 128.25 2793 348 2 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

stack Carbon Monoxide Method 10 3 120 0

stack 2,3,7,8-TCDD Method 23 3 480 0

stack 1,2,3,7,8-PeCDD Method 23 3 480 0

stack 1,2,3,4,7,8-HxCDD Method 23 3 480 0

stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0

stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Regulation Description Compound Limit Unit

Thursday, February 10, 2011 Page 2 of 31
Emissions Testing Unit 1

stack 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

stack OCDD Method 23 3 480 0

stack 2,3,7,8-TCDF Method 23 3 480 0

stack 1,2,3,7,8-PeCDF Method 23 3 480 0

stack 2,3,4,7,8-PeCDF Method 23 3 480 0

stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0

stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0

stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0

stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0

stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

stack OCDF Method 23 3 480 0

stack Other TCDD Method 23 3 480 0

stack Other PeCDD Method 23 3 480 0

stack Other HxCDD Method 23 3 480 0

stack Other HpCDD Method 23 3 480 0

stack Other TCDF Method 23 3 480 0

stack Other PeCDF Method 23 3 480 0

stack Other HxCDF Method 23 3 480 0

stack Other HpCDF Method 23 3 480 0

stack Total Dioxins Method 23 3 480 0

stack Total Furans Method 23 3 480 0

stack 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

stack 3,4,4',5-TCB (PCB81) Method 23 3 480 0

stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

stack Method 23 3 480 0

stack 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

stack Method 23 3 480 0

stack Total TEQ Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

stack Method 25A 3 120 0

stack Hydrogen Chloride Method 26 3 60 0

stack Hydrogen Fluoride Method 26 3 60 0

stack Total Particulate OTM - 27/28 3 360 0

stack Filterable Particulate OTM - 27/28 3 360 0

Inorganic (Aqueous) 

Condensible Part.

stack OTM - 27/28 3 360 0

Organic Condensible 

Particulate

stack OTM - 27/28 3 360 0

stack Filterable PM2.5 OTM - 27/28 3 360 0

stack Total PM2.5 OTM - 27/28 3 360 0

stack Manganese Method 29 3 240 0

stack Antimony Method 29 3 240 0

stack Arsenic Method 29 3 240 0

stack Beryllium Method 29 3 240 0

stack Cadmium Method 29 3 240 0

Thursday, February 10, 2011 Page 3 of 31
Emissions Testing Unit 1

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None

stack Chromium Method 29 3 240 0

stack Lead Method 29 3 240 0

stack Nickel Method 29 3 240 0

stack Selenium Method 29 3 240 0

stack Cobalt Method 29 3 240 0

stack O2 Method 3A O2 3 120 0

stack Co2 Method 3A CO2 3 120 0

stack Filterable Particulate Method 5 3 240 0

stack Sulfur Dioxide Method 6C 3 120 0

stack Nitrogen oxides (NOx) Method 7E 3 120 0

Thursday, February 10, 2011 Page 4 of 31
Emissions Testing Unit 1

Sampling / Stack Data Results Summary

Location stack - Method 10

Average

Run Number 1 2 3

Test Date 6/13/2010 6/13/2010 6/13/2010

Run Start Time 8:17:00 AM 11:00:00 

AM

1:35:00 PM

Run Finish Time 10:16:00 AM 12:59:00 

PM

3:34:00 PM

Carbon Dioxide, % 11.72 11.63 11.53 11.627

Oxygen, % 6.13 5.94 6.04 6.037

Dry Volumetric Flow Rate, dry scfm 202438 205069 201385 202,964.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 10.3 10.5 10.4 10.400

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location stack - Method 23

Average

Run Number K1-M23-1 K1-M23-2 K1-M23-3

Test Date 6/7/2010 6/8/2010 6/10/2010

Run Start Time 9:05:00 AM 7:58:00 

AM

7:22:00 AM

Run Finish Time 5:37:00 PM 4:25:00 PM 3:36:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 413.906 413.392 405.929 411.076

Moisture Content of Stack Gas, % 10.08 10.48 10.39 10.317

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.2 11.1 10.9 10.733

Oxygen, % 6.3 5.9 6.1 6.100

Average Stack Gas Temperature, °F 279.17 277.08 274.75 277.000

Dry Volumetric Flow Rate, dry scfm 212,341.8 209,473.6 206,581.2 209,465.533

Actual Wet Volumetric Flue Gas Flow Rate, acfm 332,590.9 327,531.2 321,664.2 327,262.100

Percent Isokinetic of Sampling Rate, % 98.8 100.0 100.4 99.733

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 5 of 31
Emissions Testing Unit 1

Location stack - Method 25A

Average

Run Number 1 2 3

Test Date 6/13/2010 6/13/2010 6/13/2010

Run Start Time 8:17:00 AM 11:00:00 

AM

1:35:00 PM

Run Finish Time 10:16:00 AM 12:59:00 

PM

3:34:00 PM

Carbon Dioxide, % 11.72 11.63 11.53 11.627

Oxygen, % 6.13 5.94 6.04 6.037

Dry Volumetric Flow Rate, dry scfm 202438 205069 201385 202,964.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 10.3 10.5 10.4 10.400

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location stack - Method 26

Average

Run Number K1-M26-1 K1-M26-2 K1-M26-3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:41:00 AM 9:54:00 

AM

12:08:00 PM

Run Finish Time 8:41:00 AM 10:54:00 

AM

1:08:00 PM

Net Run Time, minutes 60 60 60

Dry Gas Meter Volume Sampled, dscf 36.815 36.009 35.929 36.251

Moisture Content of Stack Gas, % 14.11 14.04 14.31 14.153

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11.78 11.78 11.76 11.773

Oxygen, % 6.11 6.08 6.11 6.100

Average Stack Gas Temperature, °F 278.00 275.00 275.00 276.000

Dry Volumetric Flow Rate, dry scfm 195,154.1 195,679.4 195,197.0 195,343.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 318,434.6 317,734.9 317,950.2 318,039.900

Percent Isokinetic of Sampling Rate, % 102.2 99.6 99.7 100.500

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 6 of 31
Emissions Testing Unit 1

Location stack - Method 29

Average

Run Number K1-M5/29-1 K1-M5/29-

2

K1-M5/29-3

Test Date 6/9/2010 6/11/2010 6/11/2010

Run Start Time 1:22:00 PM 7:31:00 

AM

12:03:00 PM

Run Finish Time 5:34:00 PM 11:43:00 

AM

4:12:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 202.379 202.558 200.779 201.905

Moisture Content of Stack Gas, % 10.42 9.89 9.68 9.997

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11 11 10.4 10.800

Oxygen, % 5.9 6.1 6.5 6.167

Average Stack Gas Temperature, °F 271.71 272.50 281.00 275.070

Dry Volumetric Flow Rate, dry scfm 205,045.1 206,489.0 206,427.2 205,987.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 318,057.8 318,757.6 321,610.4 319,475.267

Percent Isokinetic of Sampling Rate, % 100.1 99.5 99.4 99.667

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 7 of 31
Emissions Testing Unit 1

Location stack - Method 5

Average

Run Number K1-M5/29-1 K1-M5/29-

2

K1-M5/29-3

Test Date 6/9/2010 6/11/2010 6/11/2010

Run Start Time 1:22:00 PM 7:31:00 

AM

12:03:00 PM

Run Finish Time 5:34:00 PM 11:43:00 

AM

4:12:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 202.379 202.558 200.779 201.905

Moisture Content of Stack Gas, % 10.42 9.89 9.68 9.997

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11 11 10.4 10.800

Oxygen, % 5.9 6.1 6.5 6.167

Average Stack Gas Temperature, °F 271.71 272.50 281.00 275.070

Dry Volumetric Flow Rate, dry scfm 205,045.1 206,489.0 206,427.2 205,987.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 318,057.8 318,757.6 321,610.4 319,475.267

Percent Isokinetic of Sampling Rate, % 100.1 99.5 99.4 99.667

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location stack - Method 6C

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:41:00 AM 9:45:00 

AM

12:07:00 PM

Run Finish Time 9:40:00 AM 11:53:00 

AM

2:06:00 PM

Carbon Dioxide, % 11.78 11.78 11.76 11.773

Oxygen, % 6.11 6.08 6.11 6.100

Dry Volumetric Flow Rate, dry scfm 209297 209297 209297 209,297.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.9 9.9 9.9 9.900

Fuel Type Override Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 8 of 31
Emissions Testing Unit 1

Location stack - Method 7E

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 9:54:00 AM 9:54:00 

AM

12:07:00 PM

Run Finish Time 11:53:00 AM 11:53:00 

AM

2:06:00 PM

Carbon Dioxide, % 11.78 11.78 11.76 11.773

Oxygen, % 6.08 6.08 6.11 6.090

Dry Volumetric Flow Rate, dry scfm 209297 209297 209297 209,297.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.9 9.9 9.9 9.900

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location stack - OTM - 27/28

Average

Run Number k1-

otm27/28-1

K1-

OTM27/28

-2

K1-

OTM27/28-3

Test Date 6/9/2010 6/10/2010 6/14/2010

Run Start Time 12:23:00 PM 8:19:00 

AM

7:23:00 AM

Run Finish Time 6:26:00 PM 2:26:00 PM 1:35:00 PM

Net Run Time, minutes 350.5372598 355.843109

3

363.8927146

Dry Gas Meter Volume Sampled, dscf 123.220 128.049 131.039 127.436

Moisture Content of Stack Gas, % 10.14 9.94 10.28 10.120

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11 11.8 11 11.267

Oxygen, % 5.9 6.1 6 6.000

Average Stack Gas Temperature, °F 273.33 278.00 275.33 275.553

Dry Volumetric Flow Rate, dry scfm 208,114.3 209,333.0 211,321.5 209,589.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 322,525.4 325,755.0 330,007.2 326,095.867

Percent Isokinetic of Sampling Rate, % 96.1 97.8 97.0 96.967

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 9 of 31
Emissions Testing Unit 1

Emissions Summary

Location: stack - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 7.46E-04 8.67E-04 8.36E-04 0.001

ppm 7.89E-01 9.29E-01 8.90E-01 0.869

ppm@7%O2 7.43E-01 8.63E-01 8.33E-01 0.813

Location: stack - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000437 0.0000000301 0.00000000921 0.000

lb/mmBtuO2 3.06E-12 2.06E-12 6.49E-13 0.000

ng/dscm 3.73E-03 2.57E-03 8.01E-04 0.002

ng/dscm@7%O2 3.55E-03 2.38E-03 7.52E-04 0.002

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000571 0.0000000125 0.0000000134 0.000

lb/mmBtuO2 4.00E-12 8.54E-13 9.44E-13 0.000

ng/dscm 4.87E-03 1.07E-03 1.17E-03 0.002

ng/dscm@7%O2 4.64E-03 9.92E-04 1.10E-03 0.002

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000124 0.00000000811 0.0000000049 0.000

lb/mmBtuO2 8.69E-13 5.54E-13 3.45E-13 0.000

ng/dscm 1.06E-03 6.93E-04 4.26E-04 0.001

ng/dscm@7%O2 1.01E-03 6.42E-04 4.00E-04 0.001

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000213 0.0000000067 0.00000000843 0.000

lb/mmBtuO2 1.49E-12 4.58E-13 5.94E-13 0.000

ng/dscm 1.82E-03 5.72E-04 7.33E-04 0.001

ng/dscm@7%O2 1.73E-03 5.30E-04 6.88E-04 0.001

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000269 0.00000000657 0.0000000041 0.000

lb/mmBtuO2 1.88E-12 4.49E-13 2.89E-13 0.000

ng/dscm 2.30E-03 5.61E-04 3.57E-04 0.001

ng/dscm@7%O2 2.19E-03 5.20E-04 3.35E-04 0.001

Compound: 1,2,3,6,7,8-HxCDD

Average

Thursday, February 10, 2011 Page 10 of 31
Emissions Testing Unit 1

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000194 0.0000000112 0.00000000769 0.000

lb/mmBtuO2 1.36E-12 7.65E-13 5.42E-13 0.000

ng/dscm 1.66E-03 9.57E-04 6.69E-04 0.001

ng/dscm@7%O2 1.58E-03 8.87E-04 6.28E-04 0.001

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000277 0.00000000788 0.00000000532 0.000

lb/mmBtuO2 1.94E-12 5.38E-13 3.75E-13 0.000

ng/dscm 2.36E-03 6.73E-04 4.63E-04 0.001

ng/dscm@7%O2 2.25E-03 6.24E-04 4.35E-04 0.001

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000184 0.0000000105 0.00000000726 0.000

lb/mmBtuO2 1.29E-12 7.17E-13 5.12E-13 0.000

ng/dscm 1.57E-03 8.97E-04 6.32E-04 0.001

ng/dscm@7%O2 1.49E-03 8.31E-04 5.94E-04 0.001

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.00000000812 0.00000000639 0.00000000166 0.000

lb/mmBtuO2 5.69E-13 4.36E-13 1.17E-13 0.000

ng/dscm 6.93E-04 5.46E-04 1.44E-04 0.000

ng/dscm@7%O2 6.60E-04 5.06E-04 1.35E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.00000000856 0.00000000889 0.0000000055 0.000

lb/mmBtuO2 6.00E-13 6.07E-13 3.88E-13 0.000

ng/dscm 7.30E-04 7.60E-04 4.79E-04 0.001

ng/dscm@7%O2 6.95E-04 7.04E-04 4.50E-04 0.001

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.000000025 0.00000000759 0.00000000513 0.000

lb/mmBtuO2 1.75E-12 5.18E-13 3.62E-13 0.000

ng/dscm 2.13E-03 6.48E-04 4.46E-04 0.001

ng/dscm@7%O2 2.03E-03 6.00E-04 4.19E-04 0.001

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.00000000301 0.0000001 0.0000001 0.000

lb/mmBtuO2 2.11E-13 6.83E-12 7.05E-12 0.000

ng/dscm 2.57E-04 8.54E-03 8.70E-03 0.006

ng/dscm@7%O2 2.45E-04 7.91E-03 8.17E-03 0.005

Thursday, February 10, 2011 Page 11 of 31
Emissions Testing Unit 1

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.00000004698 0.00000004709 0.00000002271 0.000

lb/mmBtuO2 3.29E-12 3.22E-12 1.60E-12 0.000

ng/dscm 4.01E-03 4.02E-03 1.98E-03 0.003

ng/dscm@7%O2 3.82E-03 3.73E-03 1.86E-03 0.003

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.00000016 0.000000163 0.0000000784 0.000

lb/mmBtuO2 1.12E-11 1.11E-11 5.53E-12 0.000

ng/dscm 1.37E-02 1.39E-02 6.82E-03 0.011

ng/dscm@7%O2 1.30E-02 1.29E-02 6.41E-03 0.011

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000138 0.0000000168 0.00000000577 0.000

lb/mmBtuO2 9.67E-13 1.15E-12 4.07E-13 0.000

ng/dscm 1.18E-03 1.44E-03 5.02E-04 0.001

ng/dscm@7%O2 1.12E-03 1.33E-03 4.71E-04 0.001

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000001 0.0000001 0.0000001 0.000

lb/mmBtuO2 7.01E-12 6.83E-12 7.05E-12 0.000

ng/dscm 8.53E-03 8.54E-03 8.70E-03 0.009

ng/dscm@7%O2 8.12E-03 7.91E-03 8.17E-03 0.008

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.000000404 0.0000004 0.000000175 0.000

lb/mmBtuO2 2.83E-11 2.73E-11 1.23E-11 0.000

ng/dscm 3.45E-02 3.42E-02 1.52E-02 0.028

ng/dscm@7%O2 3.28E-02 3.17E-02 1.43E-02 0.026

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000001 0.0000001 0.0000001 0.000

lb/mmBtuO2 7.01E-12 6.83E-12 7.05E-12 0.000

ng/dscm 8.53E-03 8.54E-03 8.70E-03 0.009

ng/dscm@7%O2 8.12E-03 7.91E-03 8.17E-03 0.008

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000234 0.00000000425 0.000000004 0.000

lb/mmBtuO2 1.64E-12 2.90E-13 2.82E-13 0.000

Thursday, February 10, 2011 Page 12 of 31
Emissions Testing Unit 1

ng/dscm 2.00E-03 3.63E-04 3.48E-04 0.001

ng/dscm@7%O2 1.90E-03 3.36E-04 3.27E-04 0.001

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000309 0.000000007 0.00000000572 0.000

lb/mmBtuO2 2.17E-12 4.78E-13 4.03E-13 0.000

ng/dscm 2.64E-03 5.98E-04 4.98E-04 0.001

ng/dscm@7%O2 2.51E-03 5.54E-04 4.68E-04 0.001

Compound: 2,3,7,8-TCDD

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.00000000461 0.00000000568 0.00000000472 0.000

lb/mmBtuO2 3.23E-13 3.88E-13 3.33E-13 0.000

ng/dscm 3.93E-04 4.85E-04 4.11E-04 0.000

ng/dscm@7%O2 3.74E-04 4.49E-04 3.86E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000175 0.00000000715 0.00000000648 0.000

lb/mmBtuO2 1.23E-12 4.88E-13 4.57E-13 0.000

ng/dscm 1.49E-03 6.11E-04 5.64E-04 0.001

ng/dscm@7%O2 1.42E-03 5.66E-04 5.30E-04 0.001

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000001 0.0000001 0.0000001 0.000

lb/mmBtuO2 7.01E-12 6.83E-12 7.05E-12 0.000

ng/dscm 8.53E-03 8.54E-03 8.70E-03 0.009

ng/dscm@7%O2 8.12E-03 7.91E-03 8.17E-03 0.008

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000001 0.0000001 0.0000001 0.000

lb/mmBtuO2 7.01E-12 6.83E-12 7.05E-12 0.000

ng/dscm 8.53E-03 8.54E-03 8.70E-03 0.009

ng/dscm@7%O2 8.12E-03 7.91E-03 8.17E-03 0.008

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000000653 0.0000000537 0.0000000221 0.000

lb/mmBtuO2 4.58E-15 3.67E-12 1.56E-12 0.000

ng/dscm 5.57E-06 4.59E-03 1.92E-03 0.002

ng/dscm@7%O2 5.30E-06 4.25E-03 1.80E-03 0.002

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Thursday, February 10, 2011 Page 13 of 31
Emissions Testing Unit 1

Mass_mg 0.0000000102 0.0000001 0.0000001 0.000

lb/mmBtuO2 7.15E-13 6.83E-12 7.05E-12 0.000

ng/dscm 8.70E-04 8.54E-03 8.70E-03 0.006

ng/dscm@7%O2 8.28E-04 7.91E-03 8.17E-03 0.006

Compound: OCDD

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000827 0.000000101 0.0000000407 0.000

lb/mmBtuO2 5.79E-12 6.90E-12 2.87E-12 0.000

ng/dscm 7.06E-03 8.63E-03 3.54E-03 0.006

ng/dscm@7%O2 6.72E-03 8.00E-03 3.32E-03 0.006

Compound: OCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000253 0.00000000609 0.0000000109 0.000

lb/mmBtuO2 1.77E-12 4.16E-13 7.68E-13 0.000

ng/dscm 2.16E-03 5.20E-04 9.48E-04 0.001

ng/dscm@7%O2 2.06E-03 4.82E-04 8.90E-04 0.001

Compound: Other HpCDD

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000443 0 0 0.000

lb/mmBtuO2 3.10E-12 0.00E+00 0.00E+00 0.000

ng/dscm 3.78E-03 0.00E+00 0.00E+00 0.001

ng/dscm@7%O2 3.60E-03 0.00E+00 0.00E+00 0.001

Compound: Other HpCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000042 0 0 0.000

lb/mmBtuO2 2.94E-13 0.00E+00 0.00E+00 0.000

ng/dscm 3.58E-04 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 3.41E-04 0.00E+00 0.00E+00 0.000

Compound: Other HxCDD

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0 0.0000000077 0 0.000

lb/mmBtuO2 0.00E+00 5.26E-13 0.00E+00 0.000

ng/dscm 0.00E+00 6.58E-04 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 6.10E-04 0.00E+00 0.000

Compound: Other HxCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.00000006488 0 0 0.000

lb/mmBtuO2 4.55E-12 0.00E+00 0.00E+00 0.000

ng/dscm 5.54E-03 0.00E+00 0.00E+00 0.002

ng/dscm@7%O2 5.27E-03 0.00E+00 0.00E+00 0.002

Thursday, February 10, 2011 Page 14 of 31
Emissions Testing Unit 1

Compound: Other PeCDD

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.00000004974 0.00000000671 0 0.000

lb/mmBtuO2 3.49E-12 4.58E-13 0.00E+00 0.000

ng/dscm 4.24E-03 5.73E-04 0.00E+00 0.002

ng/dscm@7%O2 4.04E-03 5.31E-04 0.00E+00 0.002

Compound: Other PeCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000961 0.00000001441 0.00000000565 0.000

lb/mmBtuO2 6.73E-12 9.84E-13 3.98E-13 0.000

ng/dscm 8.20E-03 1.23E-03 4.92E-04 0.003

ng/dscm@7%O2 7.81E-03 1.14E-03 4.62E-04 0.003

Compound: Other TCDD

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.00000002129 0.0000000022 0 0.000

lb/mmBtuO2 1.49E-12 1.50E-13 0.00E+00 0.000

ng/dscm 1.82E-03 1.88E-04 0.00E+00 0.001

ng/dscm@7%O2 1.73E-03 1.74E-04 0.00E+00 0.001

Compound: Other TCDF

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000002215 0.00000001325 0.00000000822 0.000

lb/mmBtuO2 1.55E-11 9.05E-13 5.79E-13 0.000

ng/dscm 1.89E-02 1.13E-03 7.15E-04 0.007

ng/dscm@7%O2 1.80E-02 1.05E-03 6.72E-04 0.007

Compound: Total Dioxins

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.000000306 0.000000191 0.000000079 0.000

lb/mmBtuO2 2.14E-11 1.30E-11 5.57E-12 0.000

ng/dscm 2.61E-02 1.63E-02 6.87E-03 0.016

ng/dscm@7%O2 2.48E-02 1.51E-02 6.45E-03 0.015

Compound: Total Furans

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.000000641 0.000000089 0.00000007 0.000

lb/mmBtuO2 4.49E-11 6.08E-12 4.93E-12 0.000

ng/dscm 5.47E-02 7.60E-03 6.09E-03 0.023

ng/dscm@7%O2 5.21E-02 7.04E-03 5.72E-03 0.022

Compound: Total TEQ

Average

RunNumber K1-M23-1 K1-M23-2 K1-M23-3

Mass_mg 0.0000000431 0.00000002068 0.00000001541 0.000

lb/mmBtuO2 3.02E-12 1.41E-12 1.09E-12 0.000

Thursday, February 10, 2011 Page 15 of 31
Emissions Testing Unit 1

ng/dscm 3.68E-03 1.77E-03 1.34E-03 0.002

ng/dscm@7%O2 3.50E-03 1.64E-03 1.26E-03 0.002

Location: stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 1.57E-03 1.57E-03 1.64E-03 0.002

ppm 1.05E+00 1.07E+00 1.11E+00 1.077

ppm@7%O2 9.88E-01 9.94E-01 1.04E+00 1.007

Location: stack - Method 26

Compound: Hydrogen Chloride

Average

RunNumber K1-M26-1 K1-M26-2 K1-M26-3

Mass_mg 0.129 0.119 0.12 0.123

lb/mmBtuO2 1.00E-04 9.44E-05 9.56E-05 0.000

Compound: Hydrogen Fluoride

Average

RunNumber K1-M26-1 K1-M26-2 K1-M26-3

Mass_mg 0.213 0.217 0.205 0.212

lb/mmBtuO2 1.66E-04 1.72E-04 1.63E-04 0.000

Location: stack - Method 29

Compound: Antimony

Average

RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3

Mass_mg 0.012362 0.011242 0.007562 0.010

lb/mmBtuO2 1.72E-06 1.59E-06 1.11E-06 0.000

Compound: Arsenic

Average

RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3

Mass_mg 0.0525 0.04712 0.031493 0.044

lb/mmBtuO2 7.32E-06 6.66E-06 4.61E-06 0.000

Compound: Beryllium

Average

RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3

Mass_mg 0.00093 0.00087 0.0007 0.001

lb/mmBtuO2 1.30E-07 1.23E-07 1.03E-07 0.000

Compound: Cadmium

Average

RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3

Mass_mg 0.000637 0.000399 0.001995 0.001

lb/mmBtuO2 8.89E-08 5.64E-08 2.92E-07 0.000

Compound: Chromium

Average

RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3

Thursday, February 10, 2011 Page 16 of 31
Emissions Testing Unit 1

Mass_mg 0.01642 0.01346 0.010602 0.013

lb/mmBtuO2 2.29E-06 1.90E-06 1.55E-06 0.000

Compound: Cobalt

Average

RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3

Mass_mg 0.326993 0.309154 0.236972 0.291

lb/mmBtuO2 4.56E-05 4.37E-05 3.47E-05 0.000

Compound: Lead

Average

RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3

Mass_mg 0.014628 0.013108 0.010032 0.013

lb/mmBtuO2 2.04E-06 1.85E-06 1.47E-06 0.000

Compound: Manganese

Average

RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3

Mass_mg 0.093699 0.077159 0.05092 0.074

lb/mmBtuO2 1.31E-05 1.09E-05 7.46E-06 0.000

Compound: Nickel

Average

RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3

Mass_mg 7.99984 7.75407 5.71992 7.158

lb/mmBtuO2 1.12E-03 1.10E-03 8.38E-04 0.001

Compound: Selenium

Average

RunNumber K1-M5/29-1 K1-M5/29-2 K1-M5/29-3

Mass_mg 0.0071 0.0049 0.00457 0.006

lb/mmBtuO2 9.90E-07 6.92E-07 6.69E-07 0.000

Location: stack - Method 5

Compound: Filterable Particulate

Average

RunNumber K1-M5/29-2 K1-M5/29-3 K1-M5/29-1

Mass_mg 279.4 190.5 362 277.300

lb/mmBtuO2 3.95E-02 2.79E-02 5.05E-02 0.039

Location: stack - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 3.99E-01 3.98E-01 3.98E-01 0.398

ppm 1.85E+02 1.85E+02 1.84E+02 184.667

ppm@7%O2 1.74E+02 1.74E+02 1.73E+02 173.667

Location: stack - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

Thursday, February 10, 2011 Page 17 of 31
Emissions Testing Unit 1

Process Run Data

lb/mmBtuO2 7.70E-01 7.70E-01 7.70E-01 0.770

ppm 4.98E+02 4.97E+02 4.97E+02 497.333

ppm@7%O2 4.67E+02 4.66E+02 4.67E+02 466.667

Location: stack - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber k1-otm27/28-1 K1-OTM27/28-2 K1-OTM27/28-3

Mass_mg 236.8 191.9 190.4 206.367

lb/mmBtuO2 5.43E-02 4.29E-02 4.13E-02 0.046

Compound: Filterable PM2.5

Average

RunNumber k1-otm27/28-1 K1-OTM27/28-2 K1-OTM27/28-3

Mass_mg 139.4 119.8 109.8 123.000

lb/mmBtuO2 3.19E-02 2.68E-02 2.38E-02 0.028

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber k1-otm27/28-1 K1-OTM27/28-2 K1-OTM27/28-3

Mass_mg 24.1 23.4 27 24.833

lb/mmBtuO2 5.52E-03 5.23E-03 5.86E-03 0.006

Compound: Organic Condensible Particulate

Average

RunNumber k1-otm27/28-1 K1-OTM27/28-2 K1-OTM27/28-3

Mass_mg 13.5 4.2 9.3 9.000

lb/mmBtuO2 3.09E-03 9.38E-04 2.02E-03 0.002

Compound: Total Particulate

Average

RunNumber k1-otm27/28-1 K1-OTM27/28-2 K1-OTM27/28-3

Mass_mg 272.5 217.6 224.8 238.300

lb/mmBtuO2 6.24E-02 4.86E-02 4.88E-02 0.053

Compound: Total PM2.5

Average

RunNumber k1-otm27/28-1 K1-OTM27/28-2 K1-OTM27/28-3

Mass_mg 175.1 145.5 144.2 154.933

lb/mmBtuO2 4.01E-02 3.25E-02 3.13E-02 0.035

Thursday, February 10, 2011 Page 18 of 31
Emissions Testing Unit 1

Process Run Data

Run Name Value UOM Comments

Target

Value

1 0

2 0

1 0

2 0

1 0

2 0

1 0

2 0

1 0

2 0

1 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

2 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

1 0

1 Unit Gross Electric Generation 85.14 Mwe

1 Unit Net Electric Generation 81.41 MWh

1 Steam Output 611.4 1,000 lbs steam/hr

1 Average Heat Input 816.28 MMBtu/hr EPA Method 23: 

K1-M23-1

1 Fuel Oil Firing Rate 43.03 Klb/hr June 7, 2010 Test 

Day

3 0

3 0

3 0

3 0

3 0

3 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

3 0

3 Unit Gross Electric Generation 85.13 Mwe

3 Unit Net Electric Generation 81.41 MWh

3 Steam Output 612.2 1,000 lbs steam/hr

3 Average Heat Input 818.63 MMBtu/hr EPA Method 23: 

K1-M23-2

3 Fuel Oil Firing Rate 43.13 Klb/hr June 8, 2010 Test 

Day

4 0

Thursday, February 10, 2011 Page 19 of 31
Emissions Testing Unit 1

4 0

4 0

4 0

4 0

4 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

4 0

4 Unit Gross Electric Generation 85 Mwe

4 Unit Net Electric Generation 81.39 MWh

4 Steam Output 611.5 1,000 lbs steam/hr EPA Method 

OTM 27/28: K1-

OTM27/28-1

4 Average Heat Input 807.92 MMBtu/hr EPA Method 5/29: 

K1-M5/29-1

4 Fuel Oil Firing Rate 43.02 Klb/hr June 9, 2010 Test 

Day

5 0

5 0

5 0

5 0

5 0

5 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

5 0

5 Unit Gross Electric Generation 85.27 Mwe EPA Method 

OTM 27/28: K1-

OTM27/28-2

5 Unit Net Electric Generation 81.57 MWh EPA Method 

26/CTM-033: K1-

M26-1, K1-M26-

2, K1-M26-3

5 Steam Output 612.7 1,000 lbs steam/hr EPA Method 23: 

K1-M23-3

5 Average Heat Input 824.99 MMBtu/hr EPA Method 3A, 

6C, and 7E: Run 1, 

Run 2, Run 3

5 Fuel Oil Firing Rate 43.28 Klb/hr June 10, 2010 Test 

Day

6 0

6 0

6 0

6 0

6 0

Thursday, February 10, 2011 Page 20 of 31
Emissions Testing Unit 1

6 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

6 0

6 Unit Gross Electric Generation 85.12 Mwe

6 Unit Net Electric Generation 81.43 MWh

6 Steam Output 612 1,000 lbs steam/hr EPA Method 30B: 

K1-M30B-1, K1-

M30B-2

6 Average Heat Input 810.62 MMBtu/hr EPA Method 5/29: 

K1-M5/29-2, K1-

M5/29-3

6 Fuel Oil Firing Rate 42.98 Klb/hr June 11, 2010 Test 

Day

7 0

7 0

7 0

7 0

7 0

7 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

7 0 EPA Method 

0031/SW-846 

8260B: K1-

M0031-1, K1-

M0031-2, K1-

M0031-3

7 Unit Gross Electric Generation 85.14 Mwe EPA Method 

0010/SW-846 

8270D: K1-

M0010-1, K1-

M0010-2, K1-

M0010-3

7 Unit Net Electric Generation 81.44 MWh EPA Method 316: 

K1-M316-1, K1-

M316-2, K1-

M316-3

7 Steam Output 611.8 1,000 lbs steam/hr EPA Method 10 

and 25A: Run 1, 

Run 2, Run 3

7 Average Heat Input 813.92 MMBtu/hr EPA Method 18: 

K1-M18-1, K1-

M18-2, K1-M18-3

7 Fuel Oil Firing Rate 43 Klb/hr June 13, 2010 Test 

Day

8 0

8 0

8 0

Thursday, February 10, 2011 Page 21 of 31
Emissions Testing Unit 1

APCD Run Data

Process Lab Run Data

8 0

8 0

8 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

8 0

8 Unit Gross Electric Generation 85.1 Mwe

8 Unit Net Electric Generation 81.42 MWh

8 Steam Output 613 1,000 lbs steam/hr EPA Method 

OTM 27/28: K1-

OTM27/28-3

8 Average Heat Input 844.42 MMBtu/hr EPA Method 30B: 

K1-M30B-3

8 Fuel Oil Firing Rate 43.28 Klb/hr June 14, 2010 Test 

Day

Run Name Value UOM Comments

Target

Value

1 None 0

1 0

1 0

1 0

Run Name Value UOM Comments

1 none 0

1 0

1 0

1 0

1 0

Thursday, February 10, 2011 Page 22 of 31
Emissions Testing Unit 1

Sampling / Stack Data Results Detail

Location stack - Method 10

Average

Run Number 1 2 3

Test Date 6/13/2010 6/13/2010 6/13/2010

Run Start Time 8:17:00 AM 11:00:00 AM 1:35:00 PM

Run Finish Time 10:16:00 AM 12:59:00 PM 3:34:00 PM

Carbon Dioxide, % 11.72 11.63 11.53 11.627

Oxygen, % 6.13 5.94 6.04 6.037

Fuel Factor 1.26 1.29 1.29

Dry Volumetric Flow Rate, dry scfm 202438 205069 201385 202,964.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 10.3 10.5 10.4 10.400

Analyzer Make Thermo 

Electron

Thermo 

Electron

Thermo 

Electron

Analyzer Model 48 48 48 48.000

Analyzer Serial Number

Operating Range 0 0 0 0.000

Operating Units

No. Readings/Avg. 0 0 0 0.000

Calibration Set 0 0 0 0.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response -0.13 -0.07 -0.24 -0.147

Calibration Pre Zero Cylinder Bias -0.66 -0.33 -1.27 -0.753

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID COCC149350-

Diluted2

COCC149350-

Diluted2

COCC149350-

Diluted2

Calibration Pre High Cylinder Instrument Response 9.2 9.24 9.12 9.187

Calibration Pre High Cylinder Bias 0.33 0.55 -0.11 0.257

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response -0.07 -0.24 -0.41 -0.240

Calibration Post Zero Cylinder Bias -0.33 -1.27 -2.2 -1.267

Calibration Post Zero Cylinder Drift 0.33 0.94 0.93 0.733

Calibration Post High Cylinder ID COCC149350-

Diluted2

COCC149350-

Diluted2

COCC149350-

Diluted2

Calibration Post High Cylinder Instrument Response 9.24 9.12 8.9 9.087

Calibration Post High Cylinder Bias 0.55 -0.11 -1.32 -0.293

Calibration Post High Cylinder Drift 0.22 0.66 1.21 0.697

Cavg 0.71 0.8 0.59 0.700

Cavg Units ppmvd ppmvd ppmvd

Cgas 0.7891 0.9289 0.89 0.869

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 10, 2011 Page 23 of 31
Emissions Testing Unit 1

Location stack - Method 23

Average

Run Number K1-M23-1 K1-M23-2 K1-M23-3

Test Date 6/7/2010 6/8/2010 6/10/2010

Run Start Time 9:05:00 AM 7:58:00 AM 7:22:00 AM

Run Finish Time 5:37:00 PM 4:25:00 PM 3:36:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.26 0.26 0.259 0.260

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.03 0.98 0.98 0.997

Barometric Pressure, inches of Mercury 29.8 29.9 29.9 29.867

Average Orifice Meter Differential, inches H2O 2.75 2.65 2.51 2.637

Dry Gas Meter Volume Sampled, cubic feet 439.534 456.971 448.329 448.278

Average Dry Gas Meter Temperature, °F 119.10 115.33 114.63 116.353

Dry Gas Meter Volume Sampled, dscf 413.906 413.392 405.929 411.076

Total Moisture Liquid collected, g 985.3 1028.5 999.6 1,004.467

Volume of Water Vapor, standard cubic feet 46.38 48.41 47.05 47.280

Moisture Content of Stack Gas, % 10.08 10.48 10.39 10.317

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8992 0.8952 0.8961 0.897

Carbon Dioxide, % 10.2 11.1 10.9 10.733

Oxygen, % 6.3 5.9 6.1 6.100

Carbon Monoxide & Nitrogen, % 83.5 83 83 83.167

Fuel Factor 1.43 1.35 1.36

Dry Molecular Weight, lb/lb-Mole 29.88 30.01 29.99 29.960

Wet Molecular weight, lb/lb-Mole 28.68 28.75 28.74 28.723

Flue Gas Static Pressure, inches of H2O -0.86 -0.88 -0.82 -0.853

Absolute Flue Gas Pressure, inches of Mercury 29.74 29.84 29.84 29.807

Average Stack Gas Temperature, °F 279.17 277.08 274.75 277.000

Average Velocity Head, inches of H2O 0.8542763969

8319

0.835729409

438471

0.808369955

237497

0.833

Average Stack Gas Velocity, feet/second 61.79 60.85 59.76 60.800

Stack Cross-Sectional Area, square feet 89.710 89.710 89.710 89.710

Dry Volumetric Flow Rate, dry scfm 212,341.8 209,473.6 206,581.2 209,465.533

Actual Wet Volumetric Flue Gas Flow Rate, acfm 332,590.9 327,531.2 321,664.2 327,262.100

Percent Isokinetic of Sampling Rate, % 98.8 100.0 100.4 99.733

Percent Excess Air, % 40.0 36.8 38.6 38.467

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 128.25 128.25 128.25

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 24 of 31
Emissions Testing Unit 1

Location stack - Method 25A

Average

Run Number 1 2 3

Test Date 6/13/2010 6/13/2010 6/13/2010

Run Start Time 8:17:00 AM 11:00:00 AM 1:35:00 PM

Run Finish Time 10:16:00 AM 12:59:00 PM 3:34:00 PM

Carbon Dioxide, % 11.72 11.63 11.53 11.627

Oxygen, % 6.13 5.94 6.04 6.037

Fuel Factor 1.26 1.29 1.29

Dry Volumetric Flow Rate, dry scfm 202438 205069 201385 202,964.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 10.3 10.5 10.4 10.400

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range 0 0 0 0.000

Operating Units

No. Readings/Avg. 0 0 0 0.000

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response 0.04 0.03 0.09 0.053

Calibration Pre Zero Cylinder Bias 0 -0.13 0.66 0.177

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID THC-CC163385-

Diluted3

THC-CC163385-

Diluted3

THC-CC163385-

Diluted3

Calibration Pre High Cylinder Instrument Response 2.04 2.03 2.07 2.047

Calibration Pre High Cylinder Bias 0 -0.13 0.4 0.090

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response 0.03 0.09 0.08 0.067

Calibration Post Zero Cylinder Bias -0.13 0.66 0.53 0.353

Calibration Post Zero Cylinder Drift 0.13 0.79 0.13 0.350

Calibration Post High Cylinder ID THC-CC163385-

Diluted3

THC-CC163385-

Diluted3

THC-CC163385-

Diluted3

Calibration Post High Cylinder Instrument Response 2.03 2.07 1.99 2.030

Calibration Post High Cylinder Bias -0.13 0.4 -0.66 -0.130

Calibration Post High Cylinder Drift 0.13 0.53 1.06 0.573

Cavg 0.97 1 1.04 1.003

Cavg Units ppmvw ppmvw ppmvw

Cgas 1.0528 1.0661 1.1069 1.075

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0.94435 0.954170854

271357

0.991825192

802057

0.963

Cgasw Units ppmvw ppmvw ppmvw

Thursday, February 10, 2011 Page 25 of 31
Emissions Testing Unit 1

Location stack - Method 26

Average

Run Number K1-M26-1 K1-M26-2 K1-M26-3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:41:00 AM 9:54:00 AM 12:08:00 PM

Run Finish Time 8:41:00 AM 10:54:00 AM 1:08:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 60 60 60

Nozzle Diameter, inches 0.225 0.225 0.225 0.225

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.03 1.03 1.03 1.030

Barometric Pressure, inches of Mercury 29.9 29.9 29.9 29.900

Average Orifice Meter Differential, inches H2O 1.30 1.30 1.30 1.300

Dry Gas Meter Volume Sampled, cubic feet 38.050 37.360 37.400 37.603

Average Dry Gas Meter Temperature, °F 103.50 105.67 107.54 105.570

Dry Gas Meter Volume Sampled, dscf 36.815 36.009 35.929 36.251

Total Moisture Liquid collected, g 128.6 125 127.5 127.033

Volume of Water Vapor, standard cubic feet 6.05 5.88 6.00 5.977

Moisture Content of Stack Gas, % 14.11 14.04 14.31 14.153

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8589 0.8596 0.8569 0.858

Carbon Dioxide, % 11.78 11.78 11.76 11.773

Oxygen, % 6.11 6.08 6.11 6.100

Carbon Monoxide & Nitrogen, % 82.11 82.14 82.13 82.127

Fuel Factor 1.26 1.26 1.26

Dry Molecular Weight, lb/lb-Mole 30.13 30.13 30.13 30.130

Wet Molecular weight, lb/lb-Mole 28.42 28.43 28.39 28.413

Flue Gas Static Pressure, inches of H2O -0.82 -0.82 -0.82 -0.820

Absolute Flue Gas Pressure, inches of Mercury 29.84 29.84 29.84 29.840

Average Stack Gas Temperature, °F 278.00 275.00 275.00 276.000

Average Velocity Head, inches of H2O 0.78 0.78 0.78 0.780

Average Stack Gas Velocity, feet/second 59.16 59.03 59.07 59.087

Stack Cross-Sectional Area, square feet 89.710 89.710 89.710 89.710

Dry Volumetric Flow Rate, dry scfm 195,154.1 195,679.4 195,197.0 195,343.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 318,434.6 317,734.9 317,950.2 318,039.900

Percent Isokinetic of Sampling Rate, % 102.2 99.6 99.7 100.500

Percent Excess Air, % 39.2 39.0 39.2 39.133

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 128.25 128.25 128.25

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 26 of 31
Emissions Testing Unit 1

Location stack - Method 29

Average

Run Number K1-M5/29-1 K1-M5/29-2 K1-M5/29-3

Test Date 6/9/2010 6/11/2010 6/11/2010

Run Start Time 1:22:00 PM 7:31:00 AM 12:03:00 PM

Run Finish Time 5:34:00 PM 11:43:00 AM 4:12:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.26 0.26 0.259 0.260

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.98 1.03 1.03 1.013

Barometric Pressure, inches of Mercury 29.9 29.9 29.9 29.900

Average Orifice Meter Differential, inches H2O 2.50 2.55 2.53 2.527

Dry Gas Meter Volume Sampled, cubic feet 224.453 212.438 213.245 216.712

Average Dry Gas Meter Temperature, °F 117.02 113.56 120.81 117.130

Dry Gas Meter Volume Sampled, dscf 202.379 202.558 200.779 201.905

Total Moisture Liquid collected, g 500.1 472.3 457 476.467

Volume of Water Vapor, standard cubic feet 23.54 22.23 21.51 22.427

Moisture Content of Stack Gas, % 10.42 9.89 9.68 9.997

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8958 0.9011 0.9032 0.900

Carbon Dioxide, % 11 11 10.4 10.800

Oxygen, % 5.9 6.1 6.5 6.167

Carbon Monoxide & Nitrogen, % 83.1 82.9 83.1 83.033

Fuel Factor 1.36 1.35 1.38

Dry Molecular Weight, lb/lb-Mole 30.00 30.00 29.92 29.973

Wet Molecular weight, lb/lb-Mole 28.75 28.81 28.77 28.777

Flue Gas Static Pressure, inches of H2O -0.84 -0.83 -0.83 -0.833

Absolute Flue Gas Pressure, inches of Mercury 29.84 29.84 29.84 29.840

Average Stack Gas Temperature, °F 271.71 272.50 281.00 275.070

Average Velocity Head, inches of H2O 0.7937439071

14827

0.798188533

291531

0.802086545

763319

0.798

Average Stack Gas Velocity, feet/second 59.09 59.22 59.75 59.353

Stack Cross-Sectional Area, square feet 89.710 89.710 89.710 89.710

Dry Volumetric Flow Rate, dry scfm 205,045.1 206,489.0 206,427.2 205,987.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 318,057.8 318,757.6 321,610.4 319,475.267

Percent Isokinetic of Sampling Rate, % 100.1 99.5 99.4 99.667

Percent Excess Air, % 36.8 38.6 42.1 39.167

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 128.25 128.25 128.25

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 27 of 31
Emissions Testing Unit 1

Location stack - Method 5

Average

Run Number K1-M5/29-1 K1-M5/29-2 K1-M5/29-3

Test Date 6/9/2010 6/11/2010 6/11/2010

Run Start Time 1:22:00 PM 7:31:00 AM 12:03:00 PM

Run Finish Time 5:34:00 PM 11:43:00 AM 4:12:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.26 0.26 0.259 0.260

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.98 1.03 1.03 1.013

Barometric Pressure, inches of Mercury 29.9 29.9 29.9 29.900

Average Orifice Meter Differential, inches H2O 2.50 2.55 2.53 2.527

Dry Gas Meter Volume Sampled, cubic feet 224.453 212.438 213.245 216.712

Average Dry Gas Meter Temperature, °F 117.02 113.56 120.81 117.130

Dry Gas Meter Volume Sampled, dscf 202.379 202.558 200.779 201.905

Total Moisture Liquid collected, g 500.1 472.3 457 476.467

Volume of Water Vapor, standard cubic feet 23.54 22.23 21.51 22.427

Moisture Content of Stack Gas, % 10.42 9.89 9.68 9.997

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8958 0.9011 0.9032 0.900

Carbon Dioxide, % 11 11 10.4 10.800

Oxygen, % 5.9 6.1 6.5 6.167

Carbon Monoxide & Nitrogen, % 83.1 82.9 83.1 83.033

Fuel Factor 1.36 1.35 1.38

Dry Molecular Weight, lb/lb-Mole 30.00 30.00 29.92 29.973

Wet Molecular weight, lb/lb-Mole 28.75 28.81 28.77 28.777

Flue Gas Static Pressure, inches of H2O -0.84 -0.83 -0.83 -0.833

Absolute Flue Gas Pressure, inches of Mercury 29.84 29.84 29.84 29.840

Average Stack Gas Temperature, °F 271.71 272.50 281.00 275.070

Average Velocity Head, inches of H2O 0.7937439071

14827

0.798188533

291531

0.802086545

763319

0.798

Average Stack Gas Velocity, feet/second 59.09 59.22 59.75 59.353

Stack Cross-Sectional Area, square feet 89.710 89.710 89.710 89.710

Dry Volumetric Flow Rate, dry scfm 205,045.1 206,489.0 206,427.2 205,987.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 318,057.8 318,757.6 321,610.4 319,475.267

Percent Isokinetic of Sampling Rate, % 100.1 99.5 99.4 99.667

Percent Excess Air, % 36.8 38.6 42.1 39.167

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 128.25 128.25 128.25

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 28 of 31
Emissions Testing Unit 1

Location stack - Method 6C

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:41:00 AM 9:45:00 AM 12:07:00 PM

Run Finish Time 9:40:00 AM 11:53:00 AM 2:06:00 PM

Carbon Dioxide, % 11.78 11.78 11.76 11.773

Oxygen, % 6.11 6.08 6.11 6.100

Fuel Factor 1.26 1.26 1.26

Dry Volumetric Flow Rate, dry scfm 209297 209297 209297 209,297.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.9 9.9 9.9 9.900

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range 0 0 0 0.000

Operating Units

No. Readings/Avg. 0 0 0 0.000

Calibration Set 3 3 3 3.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response 0 1.67 1 0.890

Calibration Pre Zero Cylinder Bias 0 0.18 0.11 0.097

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID SO2-CC102092-

Diluted1

SO2-CC102092-

Diluted1

SO2-CC102092-

Diluted1

Calibration Pre High Cylinder Instrument Response 443.67 444.33 444.5 444.167

Calibration Pre High Cylinder Bias -1.54 -1.47 -1.45 -1.487

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response 1.67 1 0.67 1.113

Calibration Post Zero Cylinder Bias 0.18 0.11 0.07 0.120

Calibration Post Zero Cylinder Drift 0.18 0.07 0.04 0.097

Calibration Post High Cylinder ID SO2-CC102092-

Diluted1

SO2-CC102092-

Diluted1

SO2-CC102092-

Diluted1

Calibration Post High Cylinder Instrument Response 444.33 444.5 444.67 444.500

Calibration Post High Cylinder Bias -1.47 -1.45 -1.43 -1.450

Calibration Post High Cylinder Drift 7.0000000000

0001E-02

0.02 0.02 0.037

Cavg 179.33 179.54 179.09 179.320

Cavg Units ppmvd ppmvd ppmvd

Cgas 184.8729 184.608 184.3809 184.621

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 10, 2011 Page 29 of 31
Emissions Testing Unit 1

Location stack - Method 7E

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 9:54:00 AM 9:54:00 AM 12:07:00 PM

Run Finish Time 11:53:00 AM 11:53:00 AM 2:06:00 PM

Carbon Dioxide, % 11.78 11.78 11.76 11.773

Oxygen, % 6.08 6.08 6.11 6.090

Fuel Factor 1.26 1.26 1.26

Dry Volumetric Flow Rate, dry scfm 209297 209297 209297 209,297.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.9 9.9 9.9 9.900

Analyzer Make CAI Model CAI Model CAI Model

Analyzer Model 600 600 600 600.000

Analyzer Serial Number

Operating Range 0 0 0 0.000

Operating Units

No. Readings/Avg. 0 0 0 0.000

Calibration Set 4 4 4 4.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response 0 0.72 0.73 0.483

Calibration Pre Zero Cylinder Bias 0 0.08 0.08 0.053

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID NOx-CC187760-

Diluted1

NOx-CC187760-

Diluted1

NOx-CC187760-

Diluted1

Calibration Pre High Cylinder Instrument Response 445.3 445.02 445.08 445.133

Calibration Pre High Cylinder Bias -1.56 -1.59 -1.59 -1.580

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response 0.72 0.73 0.74 0.730

Calibration Post Zero Cylinder Bias 0.08 0.08 0.08 0.080

Calibration Post Zero Cylinder Drift 0.08 0 0 0.027

Calibration Post High Cylinder ID NOx-CC187760-

Diluted1

NOx-CC187760-

Diluted1

NOx-CC187760-

Diluted1

Calibration Post High Cylinder Instrument Response 445.02 445.08 444.03 444.710

Calibration Post High Cylinder Bias -1.59 -1.59 -1.7 -1.627

Calibration Post High Cylinder Drift 0.03 0 0.11 0.047

Cavg 483.53 483.2 482.2 482.977

Cavg Units ppmvd ppmvd ppmvd

Cgas 497.5087 497.3241 496.8478 497.227

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 10, 2011 Page 30 of 31
Emissions Testing Unit 1

Location stack - OTM - 27/28

Average

Run Number k1-otm27/28-1 K1-

OTM27/28-2

K1-

OTM27/28-3

Test Date 6/9/2010 6/10/2010 6/14/2010

Run Start Time 12:23:00 PM 8:19:00 AM 7:23:00 AM

Run Finish Time 6:26:00 PM 2:26:00 PM 1:35:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 350.5372598 355.8431093 363.8927146

Nozzle Diameter, inches 0.17 0.17 0.17 0.170

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1 1 1.03 1.010

Barometric Pressure, inches of Mercury 29.9 29.9 29.8 29.867

Average Orifice Meter Differential, inches H2O 0.44 0.48 0.45 0.457

Dry Gas Meter Volume Sampled, cubic feet 133.841 138.448 137.087 136.459

Average Dry Gas Meter Temperature, °F 113.75 111.17 107.29 110.737

Dry Gas Meter Volume Sampled, dscf 123.220 128.049 131.039 127.436

Total Moisture Liquid collected, g 295.4 300.3 319 304.900

Volume of Water Vapor, standard cubic feet 13.90 14.14 15.02 14.353

Moisture Content of Stack Gas, % 10.14 9.94 10.28 10.120

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8986 0.9006 0.8972 0.899

Carbon Dioxide, % 11 11.8 11 11.267

Oxygen, % 5.9 6.1 6 6.000

Carbon Monoxide & Nitrogen, % 83.1 82.1 83 82.733

Fuel Factor 1.36 1.25 1.35

Dry Molecular Weight, lb/lb-Mole 30.00 30.13 30.00 30.043

Wet Molecular weight, lb/lb-Mole 28.78 28.92 28.77 28.823

Flue Gas Static Pressure, inches of H2O -0.84 -0.82 -0.84 -0.833

Absolute Flue Gas Pressure, inches of Mercury 29.84 29.84 29.74 29.807

Average Stack Gas Temperature, °F 273.33 278.00 275.33 275.553

Average Velocity Head, inches of H2O 0.8153833227

39022

0.830483569

966902

0.848046785

736507

0.831

Average Stack Gas Velocity, feet/second 59.92 60.52 61.31 60.583

Stack Cross-Sectional Area, square feet 89.710 89.710 89.710 89.710

Dry Volumetric Flow Rate, dry scfm 208,114.3 209,333.0 211,321.5 209,589.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 322,525.4 325,755.0 330,007.2 326,095.867

Percent Isokinetic of Sampling Rate, % 96.1 97.8 97.0 96.967

Percent Excess Air, % 36.8 39.2 37.7 37.900

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 128.25 128.25 128.25

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 31 of 31