Wisconsin Power and Light Company

Edgewater - Unit 3

Hg CEMs Data

Voluntarily Provided to Supplement Hg/HAP ICR Data Response

On April 2, 2010, Wisconsin Power and Light Company (“WPL”) submitted its electronic response to the Utility MACT (Hg

Information Collection Request (ICR). WPL voluntarily submitted with its response a mercury continuous emission monito

(“CEMS”) report for Edgewater Unit 3. WPL submitted that report in Adobe PDF format. WPL is augmenting its original r

this Excel format of the CEMS data at the specific request of Mr. Bill Maxwell, U.S. Environmental Protection Agency. WP

the PDF version that it submitted on April 2, 2010 to be its official submittal.

The CEMS data in this file is for the period of 01/01/2009 - 12/31/2009. Start date of the time period for which Hg CEMS 

available reflects post-installation and QA/QC of the Tekran continuous mercury emission monitor system for Edgewater 

is no applicable CAMR, state or NIST QA/QC procedure applicable to the operation and maintenance of the Tekran conti

emission monitors. The mercury CEMs data includes a legend which identifies periods of start-up, shut
nic response to the Utility MACT (Hg/HAP) 

mercury continuous emission monitoring system

mat. WPL is augmenting its original response with 

nvironmental Protection Agency. WPL considers 

the time period for which Hg CEMS data is 

sion monitor system for Edgewater Unit 3. There 

nd maintenance of the Tekran continuous mercury 

up, shut-down and malfunction events.
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C

03:00 C

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00 2.1

2.2

01/02/09 7,932,097.7 268.5 1,840.0 465.6 45 60.00 2.233 0.017

2.1

01/02/09 8,917,528.2 276.0 1,840.0 542.8 53 60.00 2.255 0.020

1.9

01/02/09 9,618,926.4 275.3 1,840.0 601.2 58 60.00 2.097 0.020

1.8

01/02/09 9,322,875.5 270.2 1,840.0 572.6 55 60.00 1.931 0.018

2.3

01/02/09 9,302,870.5 258.0 1,840.0 576.4 55 60.00 1.813 0.017

3.5

01/02/09 7,320,019.4 232.7 1,840.0 413.7 40 60.00 2.539 0.017

3.2

01/02/09 5,410,134.7 228.4 1,840.0 226.4 20 60.00 5.219 0.019

3.1

01/02/09 5,410,957.4 231.2 1,840.0 226.4 20 60.00 4.772 0.017

3.0

01/02/09 5,364,814.3 236.5 1,840.0 224.5 20 60.00 4.622 0.017

6.1

01/02/09 5,349,307.2 246.8 1,840.0 223.8 20 60.00 4.473 0.016

1.8

01/02/09 6,008,603.1 264.3 1,840.0 300.4 27 60.00 7.613 0.037

1.8

01/02/09 8,453,189.0 271.1 1,840.0 514.5 50 60.00 1.845 0.015

2.0

01/02/09 8,446,046.4 272.3 1,840.0 518.7 50 60.00 1.829 0.015

2.1

01/01/09 8,509,482.0 272.5 1,840.0 517.9 50 60.00 2.050 0.017

2.1

01/01/09 8,518,732.9 272.4 1,840.0 518.5 50 60.00 2.153 0.018

2.2

01/01/09 8,565,899.1 273.1 1,840.0 516.8 50 60.00 2.172 0.018

2.2

01/01/09 8,571,909.9 272.7 1,840.0 517.1 50 60.00 2.276 0.019

2.3

01/01/09 8,505,622.2 272.1 1,840.0 517.8 50 60.00 2.255 0.019

2.3

01/01/09 8,549,376.6 272.0 1,840.0 520.4 50 60.00 2.358 0.020

2.7

01/01/09 8,564,954.5 270.9 1,840.0 521.3 50 60.00 2.358 0.020

2.1

01/01/09 8,545,976.5 268.8 1,840.0 520.2 50 60.00 2.768 0.023

2.0

01/01/09 8,468,107.4 267.7 1,840.0 515.4 50 60.00 2.153 0.018

2.0

01/01/09 8,496,950.2 267.7 1,840.0 517.2 50 60.00 2.050 0.017

2.1

01/01/09 8,520,001.4 265.5 1,840.0 518.6 50 60.00 2.050 0.017

1.9

01/01/09 8,491,178.0 259.2 1,840.0 521.5 50 60.00 2.134 0.018

2.6

01/01/09 8,417,280.2 243.5 1,840.0 521.5 49 60.00 1.914 0.016

3.1

01/01/09 6,014,687.0 224.6 1,840.0 307.3 29 60.00 3.176 0.016

2.3

01/01/09 5,357,681.1 223.6 1,840.0 230.0 20 60.00 4.505 0.017

2.4

01/01/09 5,350,867.3 225.4 1,840.0 229.7 20 60.00 3.343 0.012

2.5

01/01/09 5,338,781.7 227.1 1,840.0 229.2 20 60.00 3.488 0.013

2.1

01/01/09 5,338,298.0 228.6 1,840.0 229.2 20 60.00 3.633 0.013

3.7

01/01/09 5,331,409.6 231.5 1,840.0 228.9 20 60.00 3.052 0.011

3.2

01/01/09 5,257,902.6 240.9 1,840.0 225.8 20 60.00 5.377 0.019

2.7

01/01/09 5,473,874.8 257.6 1,840.0 252.9 24 60.00 4.322 0.017

1.8

01/01/09 8,340,213.1 266.8 1,840.0 498.6 49 60.00 2.818 0.022

2.6

01/01/09 8,534,209.0 266.0 1,840.0 528.7 51 60.00 1.813 0.015

01/01/09 8,549,141.9 267.0 1,840.0 534.3 51 60.00 2.596 0.022

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 1.5

1.4

01/04/09 5,272,110.2 251.3 1,840.0 255.0 24 60.00 1.935 0.008

1.6

01/04/09 5,970,648.1 266.3 1,840.0 288.8 29 60.00 1.806 0.008

1.7

01/03/09 8,827,109.9 273.8 1,840.0 537.3 52 60.00 1.640 0.014

1.9

01/03/09 8,854,407.8 271.9 1,840.0 538.9 52 60.00 1.743 0.015

1.7

01/03/09 8,893,440.3 270.5 1,840.0 536.5 52 60.00 1.965 0.017

1.6

01/03/09 8,855,612.3 271.0 1,840.0 534.2 52 60.00 1.758 0.015

1.5

01/03/09 8,763,896.4 271.9 1,840.0 538.2 51 60.00 1.626 0.014

1.5

01/03/09 8,833,790.9 271.2 1,840.0 542.5 51 60.00 1.524 0.013

1.7

01/03/09 8,525,298.4 267.4 1,840.0 523.5 49 60.00 1.524 0.013

1.7

01/03/09 7,913,715.1 267.6 1,840.0 477.4 45 60.00 1.758 0.013

1.6

01/03/09 8,030,922.2 270.6 1,840.0 484.5 46 60.00 1.758 0.014

1.7

01/03/09 8,665,283.3 272.5 1,840.0 527.4 50 60.00 1.640 0.014

1.6

01/03/09 8,548,354.5 272.0 1,840.0 520.3 49 60.00 1.743 0.014

1.7

01/03/09 8,568,550.6 272.1 1,840.0 521.6 49 60.00 1.640 0.014

1.8

01/03/09 8,578,826.6 271.6 1,840.0 526.9 50 60.00 1.727 0.015

2.0

01/03/09 8,612,746.3 270.1 1,840.0 529.0 50 60.00 1.829 0.015

1.8

01/03/09 8,598,722.0 269.2 1,840.0 528.1 50 60.00 2.032 0.017

1.9

01/03/09 8,223,273.6 267.5 1,840.0 500.5 47 60.00 1.845 0.015

1.8

01/03/09 8,136,441.6 265.8 1,840.0 486.4 46 60.00 1.983 0.015

1.9

01/03/09 7,978,317.7 263.8 1,840.0 476.9 45 60.00 1.879 0.014

2.1

01/03/09 7,848,670.6 263.4 1,840.0 469.2 45 60.00 1.983 0.015

2.0

01/03/09 7,918,535.3 263.2 1,840.0 460.5 45 60.00 2.253 0.017

2.0

01/03/09 7,886,600.5 262.1 1,840.0 458.6 45 60.00 2.146 0.016

1.5

01/03/09 7,861,008.4 262.6 1,840.0 452.9 45 60.00 2.166 0.016

1.7

01/03/09 7,890,226.6 263.9 1,840.0 463.1 45 60.00 1.595 0.012

1.7

01/03/09 7,931,102.7 264.1 1,840.0 465.5 45 60.00 1.807 0.013

1.7

01/02/09 7,929,737.5 263.2 1,840.0 465.5 45 60.00 1.807 0.013

1.6

01/02/09 7,880,076.0 263.7 1,840.0 471.1 45 60.00 1.774 0.013

1.5

01/02/09 7,929,601.4 264.3 1,840.0 474.1 45 60.00 1.670 0.013

1.6

01/02/09 7,943,611.1 264.0 1,840.0 474.9 45 60.00 1.566 0.012

1.4

01/02/09 7,926,073.6 264.4 1,840.0 473.8 45 60.00 1.670 0.013

1.5

01/02/09 7,941,614.3 265.4 1,840.0 474.8 45 60.00 1.461 0.011

1.6

01/02/09 7,910,932.1 265.0 1,840.0 472.9 45 60.00 1.566 0.012

1.8

01/02/09 7,931,250.1 263.9 1,840.0 474.1 45 60.00 1.670 0.013

1.7

01/02/09 7,938,383.0 263.1 1,840.0 470.2 45 60.00 1.896 0.014

1.9

01/02/09 7,955,737.8 264.0 1,840.0 471.3 45 60.00 1.791 0.013

01/02/09 7,925,989.2 264.9 1,840.0 469.5 45 60.00 2.001 0.015
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00 2.0

1.9

01/05/09 8,610,574.9 274.3 1,840.0 524.1 50 60.00 2.050 0.017

1.8

01/05/09 8,603,546.8 275.0 1,840.0 523.7 50 60.00 1.948 0.016

1.8

01/05/09 8,646,460.4 275.1 1,840.0 526.3 50 60.00 1.845 0.016

1.7

01/05/09 8,613,787.8 274.0 1,840.0 524.3 50 60.00 1.845 0.015

1.5

01/05/09 8,637,816.6 271.5 1,840.0 525.8 50 60.00 1.743 0.015

1.5

01/05/09 8,624,170.5 269.5 1,840.0 524.9 50 60.00 1.538 0.013

1.6

01/05/09 8,502,876.7 266.8 1,840.0 513.0 49 60.00 1.552 0.013

1.4

01/05/09 8,417,860.1 262.0 1,840.0 507.8 48 60.00 1.655 0.013

2.3

01/05/09 8,531,692.3 246.6 1,840.0 519.3 48 60.00 1.435 0.012

2.0

01/05/09 5,658,328.8 231.7 1,840.0 298.3 28 60.00 2.722 0.013

2.2

01/05/09 5,370,977.4 235.6 1,840.0 265.6 24 60.00 2.523 0.011

1.8

01/05/09 5,495,777.1 239.4 1,840.0 265.8 24 60.00 2.838 0.012

0.9

01/05/09 5,518,351.8 245.5 1,840.0 269.9 24 60.00 2.296 0.010

1.6

01/05/09 5,409,868.3 257.9 1,840.0 258.7 24 60.00 1.174 0.005

1.7

01/05/09 7,573,930.2 272.5 1,840.0 432.2 43 60.00 1.750 0.012

2.0

01/04/09 9,065,334.5 274.1 1,840.0 566.6 54 60.00 1.697 0.015

2.4

01/04/09 9,056,315.3 274.3 1,840.0 561.1 54 60.00 2.014 0.018

2.4

01/04/09 9,122,154.1 274.3 1,840.0 560.2 54 60.00 2.439 0.022

2.2

01/04/09 9,215,541.0 274.5 1,840.0 556.0 55 60.00 2.483 0.022

2.1

01/04/09 9,192,377.3 274.7 1,840.0 554.5 55 60.00 2.276 0.020

2.1

01/04/09 9,450,843.6 273.7 1,840.0 570.1 55 60.00 2.172 0.020

2.4

01/04/09 8,477,409.7 272.1 1,840.0 525.2 51 60.00 2.115 0.018

2.3

01/04/09 8,716,245.3 274.1 1,840.0 530.5 51 60.00 2.460 0.021

2.1

01/04/09 8,773,836.8 274.7 1,840.0 534.1 51 60.00 2.358 0.020

2.1

01/04/09 8,744,655.6 274.5 1,840.0 532.3 51 60.00 2.153 0.018

1.9

01/04/09 8,735,450.2 275.2 1,840.0 536.4 51 60.00 2.134 0.018

1.9

01/04/09 8,792,273.7 275.9 1,840.0 539.9 51 60.00 1.931 0.017

1.8

01/04/09 8,854,390.4 274.8 1,840.0 538.9 51 60.00 1.948 0.017

1.6

01/04/09 8,783,720.1 272.1 1,840.0 529.9 51 60.00 1.862 0.016

1.3

01/04/09 8,786,839.0 264.8 1,840.0 534.9 51 60.00 1.640 0.014

1.7

01/04/09 7,206,576.0 244.1 1,840.0 415.2 39 60.00 1.408 0.009

2.4

01/04/09 5,348,248.2 238.8 1,840.0 267.4 24 60.00 2.122 0.009

1.9

01/04/09 5,308,986.8 238.6 1,840.0 265.5 24 60.00 2.995 0.013

1.9

01/04/09 5,323,367.0 238.7 1,840.0 263.3 24 60.00 2.397 0.010

1.6

01/04/09 5,325,165.7 238.2 1,840.0 263.4 24 60.00 2.397 0.010

1.7

01/04/09 5,383,196.6 238.2 1,840.0 260.4 24 60.00 2.064 0.009

01/04/09 5,238,152.3 242.2 1,840.0 250.5 24 60.00 2.218 0.009
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00 C

12:00 C

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00 1.8

1.8

01/07/09 5,374,217.2 239.6 1,840.0 259.9 24 60.00 2.322 0.010

1.4

01/07/09 5,327,278.9 240.9 1,840.0 257.7 24 60.00 2.322 0.010

1.4

01/07/09 5,320,447.9 245.3 1,840.0 263.1 24 60.00 1.766 0.007

2.1

01/07/09 5,385,836.7 254.0 1,840.0 260.5 24 60.00 1.806 0.008

2.2

01/06/09 5,912,666.9 266.8 1,840.0 292.4 28 60.00 2.650 0.012

2.1

01/06/09 8,673,542.1 273.8 1,840.0 518.6 51 60.00 2.296 0.019

2.0

01/06/09 8,765,686.6 274.0 1,840.0 524.1 51 60.00 2.192 0.018

1.8

01/06/09 8,801,728.3 275.7 1,840.0 526.2 51 60.00 2.088 0.018

1.9

01/06/09 8,969,142.0 277.3 1,840.0 526.4 51 60.00 1.914 0.016

2.0

01/06/09 8,829,416.1 275.2 1,840.0 527.8 51 60.00 1.983 0.017

1.4

01/06/09 8,796,226.6 271.1 1,840.0 525.8 51 60.00 2.088 0.018

1.1

01/06/09 8,403,960.9 268.6 1,840.0 497.8 49 60.00 1.475 0.012

1.4

01/06/09 8,078,237.8 270.2 1,840.0 482.9 49 60.00 1.148 0.009

1.7

01/06/09 8,213,891.8 273.1 1,840.0 486.6 49 60.00 1.475 0.011

2.2

01/06/09 8,482,877.5 275.0 1,840.0 507.1 50 60.00 1.774 0.014

2.0

01/06/09 8,693,113.6 274.5 1,840.0 519.7 50 60.00 2.296 0.019

2.0

01/06/09 8,674,470.2 273.3 1,840.0 518.6 50 60.00 2.088 0.017

1.7

01/06/09 8,654,442.8 272.2 1,840.0 517.4 50 60.00 2.088 0.017

1.5

01/06/09 8,672,742.0 271.8 1,840.0 518.5 50 60.00 1.774 0.015

1.3

01/06/09 8,684,163.3 269.4 1,840.0 514.4 50 60.00 1.580 0.013

1.2

01/06/09 8,665,228.9 261.3 1,840.0 518.0 50 60.00 1.357 0.011

1.7

01/06/09 7,512,438.4 242.9 1,840.0 440.9 42 60.00 1.276 0.009

1.6

01/06/09 5,496,871.7 238.0 1,840.0 262.9 24 60.00 2.218 0.009

1.5

01/06/09 5,414,276.7 238.8 1,840.0 264.8 24 60.00 2.041 0.009

1.6

01/06/09 5,417,968.1 240.1 1,840.0 262.1 24 60.00 1.935 0.008

1.4

01/06/09 5,433,484.9 245.6 1,840.0 265.7 24 60.00 2.041 0.009

1.3

01/06/09 5,416,636.3 257.0 1,840.0 259.1 24 60.00 1.827 0.008

1.3

01/06/09 7,344,610.3 270.7 1,840.0 395.2 39 60.00 1.508 0.010

1.4

01/05/09 8,142,902.4 270.5 1,840.0 486.8 46 60.00 1.357 0.011

1.5

01/05/09 7,972,710.3 272.5 1,840.0 472.3 45 60.00 1.475 0.011

1.5

01/05/09 8,435,576.4 277.1 1,840.0 508.9 48 60.00 1.552 0.013

1.5

01/05/09 8,702,731.1 277.7 1,840.0 529.7 50 60.00 1.538 0.013

1.6

01/05/09 8,677,739.4 276.7 1,840.0 528.2 50 60.00 1.538 0.013

1.6

01/05/09 8,615,935.0 275.0 1,840.0 529.1 50 60.00 1.626 0.014

1.5

01/05/09 8,633,090.7 275.1 1,840.0 530.2 50 60.00 1.626 0.014

1.6

01/05/09 8,621,297.0 275.5 1,840.0 529.4 50 60.00 1.524 0.013

01/05/09 8,668,749.3 274.7 1,840.0 527.7 50 60.00 1.640 0.014
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00 1.8

1.8

01/08/09 8,037,965.9 261.4 1,840.0 493.6 48 60.00 1.829 0.014

1.2

01/08/09 8,097,464.1 261.9 1,840.0 497.3 48 60.00 1.829 0.015

1.3

01/08/09 8,274,972.7 261.1 1,840.0 499.2 48 60.00 1.241 0.010

1.1

01/08/09 8,238,795.3 259.8 1,840.0 492.5 48 60.00 1.357 0.011

1.1

01/08/09 8,192,379.7 258.8 1,840.0 512.0 50 60.00 1.098 0.009

1.3

01/08/09 7,964,087.8 259.4 1,840.0 506.4 50 60.00 1.079 0.009

1.2

01/08/09 8,038,361.9 263.8 1,840.0 506.7 51 60.00 1.287 0.010

1.1

01/08/09 8,406,684.1 264.9 1,840.0 511.7 50 60.00 1.230 0.010

1.0

01/08/09 8,352,991.2 262.5 1,840.0 513.0 50 60.00 1.118 0.009

1.6

01/08/09 8,307,426.1 258.5 1,840.0 510.2 51 60.00 1.016 0.008

1.5

01/08/09 7,917,069.0 242.4 1,840.0 473.3 47 60.00 1.670 0.013

2.9

01/08/09 6,102,562.2 226.4 1,840.0 318.4 29 60.00 1.794 0.009

1.1

01/08/09 4,620,689.7 230.4 1,840.0 211.0 19 60.00 3.964 0.013

1.6

01/08/09 4,641,078.5 242.0 1,840.0 211.9 19 60.00 1.504 0.005

1.6

01/08/09 5,222,601.9 261.3 1,840.0 261.1 23 60.00 1.997 0.008

1.6

01/08/09 8,136,430.9 273.7 1,840.0 486.4 47 60.00 1.670 0.013

1.5

01/08/09 8,851,321.9 277.8 1,840.0 548.4 53 60.00 1.611 0.014

1.5

01/07/09 8,954,418.5 277.6 1,840.0 554.8 53 60.00 1.511 0.013

1.4

01/07/09 8,900,674.1 275.5 1,840.0 551.5 53 60.00 1.511 0.013

1.5

01/07/09 8,498,592.1 275.1 1,840.0 517.3 50 60.00 1.435 0.012

1.4

01/07/09 8,646,523.4 275.5 1,840.0 531.0 51 60.00 1.524 0.013

1.5

01/07/09 8,649,006.1 275.2 1,840.0 526.5 51 60.00 1.435 0.012

1.5

01/07/09 8,550,275.6 275.6 1,840.0 511.1 50 60.00 1.566 0.013

1.6

01/07/09 8,576,694.0 275.6 1,840.0 512.8 50 60.00 1.566 0.013

1.5

01/07/09 8,546,289.8 275.2 1,840.0 510.9 50 60.00 1.670 0.014

1.4

01/07/09 8,543,735.3 275.9 1,840.0 510.8 50 60.00 1.566 0.013

1.5

01/07/09 8,554,055.0 276.1 1,840.0 516.0 50 60.00 1.448 0.012

1.5

01/07/09 8,510,313.1 275.6 1,840.0 508.8 50 60.00 1.566 0.013

1.5

01/07/09 8,530,352.1 275.8 1,840.0 514.6 50 60.00 1.552 0.013

1.6

01/07/09 8,516,838.9 276.0 1,840.0 513.8 50 60.00 1.552 0.013

1.8

01/07/09 8,522,412.3 275.3 1,840.0 514.1 50 60.00 1.655 0.014

1.7

01/07/09 8,560,240.3 274.1 1,840.0 511.7 50 60.00 1.879 0.015

1.7

01/07/09 8,493,114.7 272.9 1,840.0 512.3 50 60.00 1.758 0.014

1.2

01/07/09 8,561,567.0 267.4 1,840.0 516.5 50 60.00 1.758 0.015

1.7

01/07/09 8,255,041.4 249.7 1,840.0 498.0 47 60.00 1.241 0.010

3.0

01/07/09 5,308,950.9 239.3 1,840.0 262.6 24 60.00 2.145 0.009

01/07/09 5,365,038.0 239.5 1,840.0 262.4 24 60.00 3.827 0.016
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C

03:00 C

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 2.0 C

3.2

01/10/09 7,414,949.9 234.8 1,840.0 415.1 39 60.00 2.229 0.015

2.3

01/10/09 5,257,973.4 236.3 1,840.0 228.6 20 60.00 4.593 0.017

2.3

01/10/09 5,269,843.7 250.7 1,840.0 223.4 20 60.00 3.386 0.012

2.1

01/10/09 6,542,232.7 269.9 1,840.0 330.7 35 60.00 2.840 0.015

2.0

01/10/09 8,523,404.4 273.7 1,840.0 523.4 50 60.00 2.134 0.018

2.0

01/10/09 8,522,694.5 273.0 1,840.0 523.4 50 60.00 2.032 0.017

1.8

01/09/09 8,510,754.4 273.7 1,840.0 522.7 50 60.00 2.032 0.017

1.7

01/09/09 8,485,233.1 273.8 1,840.0 525.7 50 60.00 1.813 0.015

1.6

01/09/09 8,559,089.2 273.2 1,840.0 525.6 50 60.00 1.727 0.015

1.6

01/09/09 8,555,740.5 273.0 1,840.0 525.5 50 60.00 1.626 0.014

1.5

01/09/09 8,574,503.2 272.2 1,840.0 522.0 50 60.00 1.640 0.014

1.6

01/09/09 8,634,604.6 267.3 1,840.0 525.6 50 60.00 1.538 0.013

1.6

01/09/09 8,069,180.2 262.4 1,840.0 504.3 48 60.00 1.597 0.013

1.5

01/09/09 8,080,545.0 263.4 1,840.0 500.7 48 60.00 1.611 0.013

1.5

01/09/09 8,088,566.2 262.8 1,840.0 501.2 48 60.00 1.511 0.012

1.6

01/09/09 8,058,806.9 261.5 1,840.0 499.3 48 60.00 1.511 0.012

1.6

01/09/09 8,011,774.5 261.6 1,840.0 496.4 48 60.00 1.611 0.013

1.7

01/09/09 8,049,711.4 262.8 1,840.0 494.4 48 60.00 1.626 0.013

1.7

01/09/09 8,066,814.8 262.6 1,840.0 495.4 47 60.00 1.727 0.014

1.7

01/09/09 8,061,373.3 261.3 1,840.0 495.1 48 60.00 1.727 0.014

1.6

01/09/09 8,016,494.8 260.7 1,840.0 487.9 48 60.00 1.743 0.014

1.5

01/09/09 7,984,375.7 260.9 1,840.0 494.7 48 60.00 1.611 0.013

1.3

01/09/09 8,038,532.3 260.3 1,840.0 493.7 47 60.00 1.524 0.012

1.5

01/09/09 8,051,596.4 259.5 1,840.0 494.5 48 60.00 1.321 0.010

2.9

01/09/09 8,002,065.2 259.4 1,840.0 500.1 48 60.00 1.498 0.012

1.5

01/09/09 8,039,795.2 259.6 1,840.0 498.1 48 60.00 2.921 0.023

5.6

01/09/09 8,031,996.8 259.0 1,840.0 493.3 48 60.00 1.524 0.012

0.5

01/09/09 8,011,441.2 259.7 1,840.0 496.3 48 60.00 5.640 0.045

1.3

01/09/09 8,085,952.9 261.6 1,840.0 501.0 48 60.00 0.504 0.004

2.0

01/09/09 8,111,216.8 261.6 1,840.0 502.5 48 60.00 1.309 0.011

2.0

01/08/09 8,057,416.5 260.5 1,840.0 499.2 48 60.00 2.014 0.016

1.7

01/08/09 8,116,534.5 260.6 1,840.0 498.5 48 60.00 2.032 0.016

1.6

01/08/09 8,166,763.4 262.9 1,840.0 492.7 48 60.00 1.758 0.014

1.8

01/08/09 8,041,106.1 264.3 1,840.0 498.2 48 60.00 1.611 0.013

1.9

01/08/09 8,097,531.0 264.5 1,840.0 497.3 48 60.00 1.829 0.015

1.8

01/08/09 8,077,075.0 262.9 1,840.0 500.4 48 60.00 1.914 0.015

01/08/09 8,116,254.3 261.9 1,840.0 498.4 48 60.00 1.829 0.015
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00 3.0

3.0

01/11/09 5,195,917.8 230.7 1,840.0 231.6 20 60.00 4.201 0.016

2.2

01/11/09 5,192,544.9 230.4 1,840.0 231.4 20 60.00 4.201 0.016

2.9

01/11/09 5,167,450.0 230.8 1,840.0 230.3 20 60.00 3.080 0.011

2.9

01/11/09 5,195,654.0 231.3 1,840.0 231.6 20 60.00 4.061 0.015

2.2

01/11/09 5,195,436.5 230.4 1,840.0 234.3 20 60.00 4.012 0.015

3.8

01/11/09 5,222,612.5 228.9 1,840.0 229.9 20 60.00 3.118 0.011

3.8

01/11/09 5,162,319.8 227.6 1,840.0 230.0 20 60.00 5.321 0.020

3.6

01/11/09 5,164,640.5 227.2 1,840.0 227.4 20 60.00 5.386 0.020

2.8

01/11/09 5,151,038.4 228.4 1,840.0 229.6 20 60.00 5.041 0.019

2.8

01/11/09 5,184,777.7 230.5 1,840.0 231.1 20 60.00 3.921 0.014

2.3

01/11/09 5,201,978.1 231.5 1,840.0 231.8 20 60.00 3.921 0.015

3.0

01/11/09 5,207,828.6 233.5 1,840.0 232.1 20 60.00 3.220 0.012

2.5

01/11/09 5,152,328.2 239.0 1,840.0 229.6 20 60.00 4.201 0.015

3.2

01/11/09 5,149,216.8 253.0 1,840.0 226.7 20 60.00 3.544 0.013

2.2

01/11/09 6,799,726.5 268.9 1,840.0 354.8 36 60.00 3.827 0.022

2.4

01/11/09 8,568,473.0 272.4 1,840.0 516.9 50 60.00 2.276 0.019

2.0

01/11/09 8,566,225.9 271.7 1,840.0 512.1 50 60.00 2.505 0.021

2.0

01/11/09 8,550,804.2 270.4 1,840.0 520.5 50 60.00 2.050 0.017

2.7

01/11/09 8,561,951.1 269.4 1,840.0 521.2 50 60.00 2.050 0.017

2.4

01/10/09 8,566,869.9 269.1 1,840.0 516.8 50 60.00 2.793 0.023

2.5

01/10/09 8,509,610.0 270.4 1,840.0 513.4 50 60.00 2.483 0.020

2.5

01/10/09 8,608,619.8 270.6 1,840.0 519.3 50 60.00 2.586 0.021

2.4

01/10/09 8,533,106.3 270.6 1,840.0 519.4 50 60.00 2.563 0.021

2.4

01/10/09 8,517,471.2 272.6 1,840.0 518.4 50 60.00 2.460 0.020

2.4

01/10/09 8,573,235.7 273.7 1,840.0 521.8 50 60.00 2.460 0.021

2.8

01/10/09 8,552,973.6 273.3 1,840.0 520.6 50 60.00 2.460 0.020

2.7

01/10/09 8,524,909.6 271.3 1,840.0 518.9 50 60.00 2.870 0.024

2.6

01/10/09 8,532,059.9 269.2 1,840.0 519.3 50 60.00 2.768 0.023

1.9

01/10/09 8,710,589.4 267.8 1,840.0 520.8 50 60.00 2.714 0.023

1.8

01/10/09 8,268,236.5 267.5 1,840.0 503.3 50 60.00 1.948 0.016

1.8

01/10/09 8,481,627.4 267.8 1,840.0 511.7 50 60.00 1.862 0.015

1.8

01/10/09 8,553,327.6 266.9 1,840.0 511.3 50 60.00 1.879 0.015

1.5

01/10/09 8,687,253.1 265.4 1,840.0 514.6 50 60.00 1.896 0.016

1.9

01/10/09 8,302,613.9 266.3 1,840.0 496.4 50 60.00 1.566 0.012

1.9

01/10/09 8,453,044.5 266.8 1,840.0 519.1 50 60.00 1.931 0.016

1.9

01/10/09 8,525,133.6 262.8 1,840.0 523.5 50 60.00 1.931 0.016

01/10/09 8,564,934.2 253.8 1,840.0 526.0 50 60.00 1.931 0.016
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00 2.3

3.0

01/13/09 8,519,770.6 269.4 1,840.0 518.6 49 60.00 2.358 0.020

2.4

01/13/09 8,609,280.2 268.4 1,840.0 524.0 50 60.00 3.075 0.026

3.5

01/13/09 8,661,316.8 260.2 1,840.0 527.2 50 60.00 2.460 0.021

2.8

01/13/09 7,727,394.2 237.4 1,840.0 440.9 42 60.00 3.827 0.027

2.9

01/13/09 5,247,541.9 231.3 1,840.0 228.2 20 60.00 4.019 0.015

3.3

01/13/09 5,232,152.5 234.4 1,840.0 230.3 20 60.00 4.111 0.015

1.6

01/13/09 5,221,440.1 240.7 1,840.0 232.7 20 60.00 4.621 0.017

1.7

01/13/09 5,242,218.7 254.2 1,840.0 227.9 20 60.00 2.296 0.008

1.9

01/12/09 6,887,462.1 269.9 1,840.0 370.6 37 60.00 1.972 0.012

1.9

01/12/09 8,526,879.2 272.9 1,840.0 519.0 50 60.00 1.948 0.016

2.1

01/12/09 8,517,963.8 273.3 1,840.0 518.5 50 60.00 1.948 0.016

2.0

01/12/09 8,547,095.7 273.2 1,840.0 520.3 50 60.00 2.153 0.018

2.1

01/12/09 8,519,115.0 273.6 1,840.0 518.5 50 60.00 2.050 0.017

2.2

01/12/09 8,560,515.8 273.9 1,840.0 516.5 50 60.00 2.172 0.018

2.2

01/12/09 8,594,349.2 273.7 1,840.0 518.4 50 60.00 2.276 0.019

2.2

01/12/09 8,578,674.3 272.6 1,840.0 517.5 50 60.00 2.276 0.019

2.2

01/12/09 8,583,216.8 272.4 1,840.0 517.8 50 60.00 2.276 0.019

2.4

01/12/09 8,580,790.4 272.6 1,840.0 522.3 50 60.00 2.255 0.019

2.3

01/12/09 8,564,311.6 272.0 1,840.0 521.3 50 60.00 2.460 0.021

2.0

01/12/09 8,539,700.0 271.5 1,840.0 524.5 50 60.00 2.337 0.020

2.1

01/12/09 8,529,154.4 271.9 1,840.0 523.8 50 60.00 2.032 0.017

2.2

01/12/09 8,551,692.5 271.2 1,840.0 520.6 50 60.00 2.153 0.018

2.0

01/12/09 8,548,387.4 268.3 1,840.0 520.3 50 60.00 2.255 0.019

1.4

01/12/09 8,544,777.8 263.4 1,840.0 520.1 50 60.00 2.050 0.017

2.7

01/12/09 8,581,350.0 247.7 1,840.0 522.3 50 60.00 1.435 0.012

2.5

01/12/09 5,809,043.5 227.9 1,840.0 299.9 27 60.00 3.263 0.016

3.1

01/12/09 5,256,931.5 226.0 1,840.0 228.6 20 60.00 3.588 0.013

2.0

01/12/09 5,163,183.9 226.4 1,840.0 218.9 20 60.00 4.563 0.016

2.3

01/12/09 5,209,622.7 227.9 1,840.0 220.9 20 60.00 2.944 0.010

2.2

01/12/09 5,195,194.1 228.9 1,840.0 223.0 20 60.00 3.343 0.012

3.2

01/12/09 5,178,174.1 228.6 1,840.0 233.6 20 60.00 3.043 0.011

2.6

01/12/09 5,113,133.5 229.3 1,840.0 230.6 20 60.00 4.427 0.016

2.6

01/11/09 5,181,965.0 230.1 1,840.0 230.9 20 60.00 3.641 0.013

2.1

01/11/09 5,185,848.1 229.7 1,840.0 233.9 20 60.00 3.597 0.013

3.6

01/11/09 5,185,038.6 229.0 1,840.0 231.1 20 60.00 2.940 0.011

3.0

01/11/09 5,131,351.2 228.9 1,840.0 231.5 20 60.00 4.980 0.018

01/11/09 5,131,807.0 230.2 1,840.0 231.5 20 60.00 4.150 0.015
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

08:00 C

09:00 C

10:00 C

11:00 C

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00 1.7

1.7

01/14/09 8,608,312.4 269.8 1,840.0 528.6 50 60.00 1.727 0.015

1.7

01/14/09 8,577,328.2 267.4 1,840.0 522.1 50 60.00 1.743 0.015

1.7

01/14/09 8,544,670.2 266.1 1,840.0 524.8 50 60.00 1.727 0.014

1.5

01/14/09 8,578,120.5 267.7 1,840.0 526.8 50 60.00 1.727 0.015

1.5

01/14/09 8,593,753.7 269.0 1,840.0 523.1 50 60.00 1.538 0.013

1.8

01/14/09 8,612,861.7 269.3 1,840.0 524.3 50 60.00 1.538 0.013

1.8

01/14/09 8,559,177.4 269.7 1,840.0 525.6 50 60.00 1.829 0.015

1.6

01/14/09 8,557,715.0 271.6 1,840.0 525.6 50 60.00 1.829 0.015

1.8

01/14/09 8,510,164.7 271.4 1,840.0 522.6 50 60.00 1.626 0.014

1.9

01/14/09 8,531,112.4 270.6 1,840.0 523.9 50 60.00 1.829 0.015

1.6

01/14/09 8,488,520.7 268.4 1,840.0 525.9 50 60.00 1.914 0.016

1.6

01/14/09 8,505,674.5 268.1 1,840.0 522.4 50 60.00 1.626 0.014

1.6

01/14/09 8,548,683.2 268.3 1,840.0 525.0 50 60.00 1.626 0.014

1.6

01/14/09 8,684,329.2 267.2 1,840.0 533.3 50 60.00 1.626 0.014

1.5

01/14/09 8,692,001.2 263.5 1,840.0 529.1 50 60.00 1.640 0.014

3.0

01/14/09 8,696,017.2 251.0 1,840.0 529.3 50 60.00 1.538 0.013

1.9

01/14/09 6,387,660.4 233.0 1,840.0 347.2 32 60.00 3.444 0.019

1.7

01/14/09 5,403,486.7 234.3 1,840.0 252.5 22 60.00 2.537 0.010

1.8

01/14/09 5,397,894.2 242.9 1,840.0 258.2 22 60.00 2.218 0.009

1.6

01/14/09 5,480,509.5 257.8 1,840.0 247.2 21 60.00 2.490 0.010

1.5

01/14/09 8,566,357.8 270.4 1,840.0 521.4 49 60.00 1.640 0.014

1.7

01/13/09 8,829,051.4 271.1 1,840.0 542.2 51 60.00 1.524 0.013

1.9

01/13/09 8,812,723.9 270.5 1,840.0 541.2 51 60.00 1.727 0.015

1.8

01/13/09 8,793,454.9 269.3 1,840.0 540.0 51 60.00 1.931 0.017

1.7

01/13/09 8,765,862.2 269.7 1,840.0 538.3 51 60.00 1.829 0.016

1.8

01/13/09 8,769,033.4 271.0 1,840.0 538.5 51 60.00 1.727 0.015

1.9

01/13/09 8,821,457.9 271.3 1,840.0 541.7 51 60.00 1.829 0.016

1.9

01/13/09 8,818,677.5 270.4 1,840.0 541.6 51 60.00 1.931 0.017

1.8

01/13/09 8,788,281.0 270.3 1,840.0 539.7 51 60.00 1.931 0.017

1.8

01/13/09 8,800,944.7 272.1 1,840.0 540.5 51 60.00 1.829 0.016

1.9

01/13/09 8,806,477.4 272.4 1,840.0 540.8 51 60.00 1.829 0.016

1.8

01/13/09 8,770,172.0 272.3 1,840.0 538.6 51 60.00 1.931 0.017

1.8

01/13/09 8,797,585.3 271.5 1,840.0 540.3 51 60.00 1.829 0.016

2.7

01/13/09 8,362,073.3 268.4 1,840.0 513.5 48 60.00 1.829 0.015

1.1

01/13/09 8,110,554.7 271.5 1,840.0 484.9 47 60.00 2.818 0.022

5.4

01/13/09 8,510,694.2 271.0 1,840.0 518.1 49 60.00 1.128 0.009

01/13/09 8,493,421.1 269.3 1,840.0 517.0 49 60.00 5.536 0.046
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C

03:00 C

04:00 C

05:00 C

06:00

07:00

08:00

09:00 0.9 C

0.8

01/16/09 9,136,354.9 273.4 1,840.0 541.2 50 60.00 0.948 0.008

0.9

01/16/09 9,086,930.0 271.4 1,840.0 543.2 50 60.00 0.835 0.007

0.9

01/16/09 9,000,836.0 270.6 1,840.0 538.1 50 60.00 0.939 0.008

0.9

01/16/09 9,018,068.4 271.5 1,840.0 539.1 50 60.00 0.939 0.008

2.7

01/16/09 9,053,545.6 272.4 1,840.0 536.4 50 60.00 0.948 0.008

1.0

01/16/09 9,045,690.2 272.1 1,840.0 535.9 50 60.00 2.844 0.024

7.6

01/16/09 9,026,566.7 270.7 1,840.0 534.8 50 60.00 1.053 0.009

0.9

01/16/09 8,941,667.5 270.7 1,840.0 529.7 50 60.00 8.006 0.068

1.0

01/16/09 8,970,640.3 271.3 1,840.0 541.2 50 60.00 0.931 0.008

1.2

01/16/09 8,998,501.7 270.2 1,840.0 538.0 50 60.00 1.044 0.009

1.1

01/15/09 8,920,864.3 269.8 1,840.0 538.2 50 60.00 1.241 0.011

1.1

01/15/09 8,933,142.0 272.1 1,840.0 538.9 50 60.00 1.138 0.010

1.2

01/15/09 8,905,307.8 272.6 1,840.0 542.0 50 60.00 1.128 0.010

1.3

01/15/09 8,938,268.4 271.5 1,840.0 544.1 50 60.00 1.230 0.011

2.7

01/15/09 8,957,427.7 271.9 1,840.0 545.2 50 60.00 1.333 0.012

1.9

01/15/09 8,929,810.8 273.1 1,840.0 543.6 50 60.00 2.768 0.024

1.5

01/15/09 9,015,657.4 273.8 1,840.0 543.9 50 60.00 1.965 0.017

1.6

01/15/09 9,153,725.0 271.8 1,840.0 547.3 50 60.00 1.566 0.014

1.8

01/15/09 8,846,783.3 267.9 1,840.0 538.5 50 60.00 1.640 0.014

1.7

01/15/09 8,712,634.7 268.9 1,840.0 535.1 50 60.00 1.829 0.016

1.6

01/15/09 8,644,430.6 268.4 1,840.0 530.9 50 60.00 1.727 0.015

1.7

01/15/09 8,720,769.4 266.5 1,840.0 530.8 50 60.00 1.640 0.014

1.5

01/15/09 8,596,436.2 262.8 1,840.0 527.9 50 60.00 1.727 0.015

1.5

01/15/09 8,492,417.4 263.5 1,840.0 526.1 50 60.00 1.511 0.013

1.5

01/15/09 8,548,568.8 265.3 1,840.0 529.7 50 60.00 1.511 0.013

1.5

01/15/09 8,498,238.1 264.9 1,840.0 531.1 50 60.00 1.498 0.013

1.6

01/15/09 8,527,030.5 264.1 1,840.0 528.3 50 60.00 1.511 0.013

1.4

01/15/09 8,516,670.1 263.9 1,840.0 527.7 50 60.00 1.611 0.014

2.9

01/15/09 8,557,844.9 265.3 1,840.0 525.6 50 60.00 1.422 0.012

1.5

01/15/09 8,543,620.9 266.2 1,840.0 524.7 50 60.00 2.947 0.025

1.5

01/15/09 8,567,043.5 266.4 1,840.0 521.5 50 60.00 1.538 0.013

1.0

01/15/09 8,597,238.2 267.3 1,840.0 523.3 50 60.00 1.538 0.013

1.2

01/15/09 8,542,816.9 268.3 1,840.0 529.3 50 60.00 1.007 0.009

1.6

01/15/09 8,560,536.1 268.4 1,840.0 530.4 50 60.00 1.209 0.010

1.7

01/14/09 8,532,993.8 267.9 1,840.0 528.7 50 60.00 1.611 0.014

1.7

01/14/09 8,505,660.0 269.1 1,840.0 531.6 50 60.00 1.697 0.014

01/14/09 8,560,970.6 270.5 1,840.0 530.4 50 60.00 1.712 0.015
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

10:00 C

11:00 C

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00 0.8

0.8

01/17/09 9,094,477.0 278.2 1,840.0 533.8 50 60.00 0.850 0.007

0.6

01/17/09 9,178,874.8 279.4 1,840.0 533.8 50 60.00 0.858 0.007

0.6

01/17/09 9,174,863.7 280.2 1,840.0 533.5 50 60.00 0.644 0.005

0.8

01/17/09 9,182,773.4 280.2 1,840.0 529.0 50 60.00 0.650 0.005

0.9

01/17/09 9,199,860.3 280.0 1,840.0 530.0 50 60.00 0.867 0.007

0.9

01/17/09 9,256,738.1 280.5 1,840.0 533.3 50 60.00 0.975 0.008

1.1

01/17/09 9,188,851.1 281.2 1,840.0 529.4 50 60.00 0.975 0.008

0.9

01/17/09 9,186,519.7 280.9 1,840.0 534.2 50 60.00 1.180 0.010

0.8

01/17/09 9,201,174.4 278.6 1,840.0 530.1 50 60.00 0.975 0.008

0.6

01/17/09 9,171,580.9 277.2 1,840.0 528.4 50 60.00 0.867 0.007

0.6

01/17/09 9,155,320.3 276.8 1,840.0 527.4 50 60.00 0.650 0.005

0.7

01/17/09 9,168,208.0 275.6 1,840.0 528.2 50 60.00 0.650 0.005

0.9

01/17/09 9,146,634.8 272.2 1,840.0 526.9 50 60.00 0.758 0.006

0.9

01/17/09 8,958,203.6 264.0 1,840.0 525.8 50 60.00 0.957 0.008

1.4

01/17/09 8,711,173.2 247.1 1,840.0 520.8 50 60.00 0.939 0.008

1.2

01/17/09 5,710,369.6 233.1 1,840.0 297.9 27 60.00 1.674 0.008

0.9

01/17/09 5,326,138.4 238.1 1,840.0 260.5 24 60.00 1.531 0.006

2.7

01/17/09 5,350,547.6 250.7 1,840.0 261.7 24 60.00 1.148 0.005

0.8

01/17/09 6,753,929.7 269.3 1,840.0 345.0 33 60.00 3.298 0.018

0.9

01/17/09 9,231,892.8 275.1 1,840.0 526.8 50 60.00 0.875 0.007

0.7

01/17/09 9,157,258.9 274.3 1,840.0 527.5 50 60.00 0.975 0.008

0.5

01/17/09 9,105,251.5 274.5 1,840.0 539.4 50 60.00 0.737 0.006

0.7

01/17/09 9,161,337.9 275.2 1,840.0 537.7 50 60.00 0.532 0.005

0.9

01/16/09 9,163,991.3 275.6 1,840.0 542.9 50 60.00 0.737 0.006

0.9

01/16/09 9,182,365.1 274.3 1,840.0 538.9 50 60.00 0.957 0.008

0.8

01/16/09 9,206,251.3 275.0 1,840.0 545.4 50 60.00 0.948 0.008

0.7

01/16/09 9,159,897.7 276.2 1,840.0 542.6 50 60.00 0.843 0.007

0.8

01/16/09 9,176,466.8 276.4 1,840.0 543.6 50 60.00 0.737 0.006

0.7

01/16/09 9,205,927.4 276.7 1,840.0 540.4 50 60.00 0.850 0.007

0.7

01/16/09 9,231,056.8 278.0 1,840.0 536.8 50 60.00 0.751 0.006

0.8

01/16/09 9,172,995.9 278.1 1,840.0 533.4 50 60.00 0.751 0.006

1.0

01/16/09 9,167,953.9 277.0 1,840.0 538.1 50 60.00 0.850 0.007

1.0

01/16/09 9,125,826.7 276.2 1,840.0 535.7 50 60.00 1.063 0.009

1.0

01/16/09 9,144,130.7 277.4 1,840.0 531.7 50 60.00 1.073 0.009

1.2

01/16/09 9,192,275.5 277.9 1,840.0 544.5 50 60.00 1.053 0.009

5.3

01/16/09 9,201,658.3 275.9 1,840.0 545.1 50 60.00 1.264 0.011

01/16/09 9,187,422.6 273.9 1,840.0 544.2 50 60.00 5.583 0.049
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00 0.5

0.5

01/19/09 9,009,488.6 276.5 1,840.0 528.8 50 60.00 0.532 0.004

0.4

01/19/09 9,017,469.0 276.9 1,840.0 529.3 50 60.00 0.532 0.004

0.4

01/19/09 9,038,503.0 276.7 1,840.0 530.6 50 60.00 0.425 0.004

0.3

01/19/09 8,951,439.2 275.8 1,840.0 530.2 50 60.00 0.421 0.004

0.2

01/19/09 8,988,120.9 277.0 1,840.0 527.6 50 60.00 0.319 0.003

0.3

01/19/09 9,018,394.2 277.7 1,840.0 524.4 50 60.00 0.215 0.002

2.7

01/19/09 9,019,272.9 277.0 1,840.0 524.5 50 60.00 0.322 0.003

0.5

01/19/09 8,947,003.4 275.1 1,840.0 525.2 49 60.00 2.870 0.024

0.5

01/19/09 8,773,401.4 277.8 1,840.0 505.4 48 60.00 0.542 0.004

0.2

01/19/09 9,039,247.8 277.8 1,840.0 520.7 50 60.00 0.542 0.005

0.2

01/19/09 9,086,705.0 276.6 1,840.0 533.4 50 60.00 0.213 0.002

0.3

01/19/09 9,037,009.5 275.9 1,840.0 530.4 50 60.00 0.213 0.002

0.3

01/18/09 9,016,336.3 275.7 1,840.0 529.2 50 60.00 0.319 0.003

0.1

01/18/09 9,058,389.7 274.3 1,840.0 526.7 50 60.00 0.322 0.003

0.2

01/18/09 9,059,871.6 272.5 1,840.0 521.9 50 60.00 0.108 0.001

0.1

01/18/09 8,943,200.8 271.9 1,840.0 515.2 50 60.00 0.217 0.002

0.2

01/18/09 8,971,445.2 272.8 1,840.0 511.9 50 60.00 0.109 0.001

0.2

01/18/09 8,968,009.2 272.6 1,840.0 516.6 50 60.00 0.217 0.002

0.2

01/18/09 8,901,931.9 272.6 1,840.0 512.8 50 60.00 0.217 0.002

0.2

01/18/09 9,051,433.4 273.4 1,840.0 516.5 50 60.00 0.219 0.002

0.3

01/18/09 9,065,688.5 273.7 1,840.0 522.3 50 60.00 0.217 0.002

0.4

01/18/09 9,012,796.5 271.7 1,840.0 529.0 50 60.00 0.319 0.003

0.4

01/18/09 8,875,259.5 271.0 1,840.0 525.7 50 60.00 0.421 0.004

0.7

01/18/09 8,853,479.7 269.5 1,840.0 524.4 51 60.00 0.421 0.004

0.8

01/18/09 8,895,939.5 265.1 1,840.0 531.8 51 60.00 0.731 0.006

1.4

01/18/09 8,620,399.0 243.5 1,840.0 515.3 49 60.00 0.835 0.007

1.4

01/18/09 5,341,065.9 229.6 1,840.0 267.1 25 60.00 1.747 0.007

1.3

01/18/09 5,372,370.7 230.0 1,840.0 262.8 24 60.00 1.786 0.008

0.9

01/18/09 5,409,475.3 231.3 1,840.0 261.6 24 60.00 1.677 0.007

1.0

01/18/09 5,402,190.1 235.2 1,840.0 258.4 24 60.00 1.174 0.005

2.7

01/18/09 5,325,402.3 242.9 1,840.0 257.6 24 60.00 1.290 0.005

0.7

01/18/09 5,497,765.8 255.6 1,840.0 265.9 24 60.00 3.483 0.015

0.7

01/18/09 7,082,504.7 271.8 1,840.0 354.1 34 60.00 0.874 0.005

1.2

01/18/09 8,983,581.3 276.3 1,840.0 517.6 50 60.00 0.758 0.006

0.5

01/18/09 9,081,635.9 277.8 1,840.0 528.1 50 60.00 1.288 0.011

0.7

01/18/09 9,128,866.1 278.4 1,840.0 530.9 50 60.00 0.537 0.005

01/17/09 9,079,568.2 278.5 1,840.0 528.0 50 60.00 0.751 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00 0.3

0.2

01/21/09 8,990,224.4 276.4 1,840.0 522.8 49 60.00 0.322 0.003

0.5

01/20/09 9,070,599.5 276.8 1,840.0 522.6 49 60.00 0.217 0.002

0.4

01/20/09 8,974,121.9 276.5 1,840.0 517.0 49 60.00 0.542 0.004

2.9

01/20/09 9,004,480.5 277.8 1,840.0 523.6 49 60.00 0.429 0.004

1.0

01/20/09 9,041,153.5 278.7 1,840.0 520.8 49 60.00 3.141 0.026

0.7

01/20/09 9,052,732.9 278.9 1,840.0 521.5 49 60.00 1.083 0.009

0.6

01/20/09 9,029,478.1 277.3 1,840.0 525.1 49 60.00 0.751 0.006

1.6

01/20/09 8,944,482.9 277.3 1,840.0 520.1 48 60.00 0.644 0.005

7.1

01/20/09 9,053,244.0 276.7 1,840.0 516.6 48 60.00 1.750 0.014

0.8

01/20/09 8,671,148.6 274.8 1,840.0 504.2 48 60.00 7.619 0.061

0.6

01/20/09 8,670,599.7 277.1 1,840.0 509.0 49 60.00 0.850 0.007

0.2

01/20/09 9,134,262.0 279.9 1,840.0 521.2 50 60.00 0.656 0.005

2.8

01/20/09 9,121,244.4 280.9 1,840.0 530.4 50 60.00 0.215 0.002

8.4

01/20/09 9,141,481.2 280.0 1,840.0 536.5 50 60.00 2.977 0.026

3.1

01/20/09 9,127,699.4 279.0 1,840.0 535.8 50 60.00 8.930 0.077

1.9

01/20/09 9,093,966.9 277.5 1,840.0 533.8 50 60.00 3.296 0.028

0.5

01/20/09 9,160,354.5 278.7 1,840.0 537.7 50 60.00 2.020 0.017

0.5

01/20/09 9,170,705.2 278.9 1,840.0 538.3 50 60.00 0.532 0.005

0.5

01/20/09 9,158,086.2 278.3 1,840.0 537.5 50 60.00 0.532 0.005

2.6

01/20/09 9,137,034.7 278.8 1,840.0 536.3 50 60.00 0.532 0.005

0.5

01/20/09 9,140,023.6 279.5 1,840.0 536.5 50 60.00 2.764 0.024

0.6

01/20/09 9,014,461.7 279.1 1,840.0 529.1 50 60.00 0.532 0.004

0.6

01/20/09 8,879,043.7 278.3 1,840.0 511.5 50 60.00 0.650 0.005

0.8

01/20/09 9,011,556.2 277.6 1,840.0 533.9 50 60.00 0.632 0.005

0.5

01/20/09 9,028,842.8 276.2 1,840.0 530.0 50 60.00 0.850 0.007

0.4

01/19/09 8,994,508.0 275.2 1,840.0 528.0 50 60.00 0.532 0.004

0.4

01/19/09 8,991,382.4 275.9 1,840.0 527.7 50 60.00 0.425 0.004

0.4

01/19/09 8,989,399.1 276.5 1,840.0 527.6 50 60.00 0.425 0.004

0.4

01/19/09 9,004,503.8 276.7 1,840.0 528.6 50 60.00 0.425 0.004

0.4

01/19/09 9,000,154.2 277.7 1,840.0 533.2 50 60.00 0.421 0.004

0.5

01/19/09 9,007,050.5 278.8 1,840.0 528.7 50 60.00 0.425 0.004

0.5

01/19/09 9,012,621.0 279.1 1,840.0 529.0 50 60.00 0.532 0.004

0.8

01/19/09 8,997,851.0 277.5 1,840.0 533.0 50 60.00 0.527 0.004

0.6

01/19/09 9,086,941.6 277.2 1,840.0 533.4 50 60.00 0.850 0.007

0.6

01/19/09 9,074,351.7 278.1 1,840.0 532.6 50 60.00 0.638 0.005

0.4

01/19/09 9,051,161.8 277.8 1,840.0 531.3 50 60.00 0.638 0.005

01/19/09 9,071,047.6 276.2 1,840.0 527.5 50 60.00 0.429 0.004
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00 C

22:00 C

23:00 C

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00 2.9

1.7

01/22/09 8,958,140.5 275.9 1,840.0 525.8 50 60.00 3.083 0.026

0.9

01/22/09 9,110,774.5 277.8 1,840.0 529.8 50 60.00 1.824 0.015

0.8

01/22/09 9,129,735.0 278.6 1,840.0 535.9 50 60.00 0.957 0.008

0.2

01/22/09 9,128,343.4 278.1 1,840.0 535.8 50 60.00 0.850 0.007

0.5

01/22/09 9,140,213.7 277.1 1,840.0 536.5 50 60.00 0.213 0.002

1.0

01/22/09 9,224,707.5 277.3 1,840.0 536.5 50 60.00 0.537 0.005

1.2

01/22/09 9,188,587.3 277.1 1,840.0 529.4 50 60.00 1.083 0.009

1.3

01/22/09 9,177,874.9 276.2 1,840.0 528.7 50 60.00 1.300 0.011

2.8

01/22/09 9,147,529.9 275.6 1,840.0 527.0 50 60.00 1.408 0.012

0.5

01/22/09 9,172,841.7 276.3 1,840.0 528.4 50 60.00 3.033 0.026

1.0

01/22/09 9,156,555.8 276.9 1,840.0 522.5 50 60.00 0.547 0.005

1.1

01/22/09 9,234,941.8 276.4 1,840.0 527.0 50 60.00 1.093 0.009

0.6

01/22/09 9,122,911.5 276.4 1,840.0 530.5 50 60.00 1.180 0.010

0.8

01/22/09 9,146,912.1 278.6 1,840.0 531.9 50 60.00 0.644 0.005

2.7

01/21/09 9,170,081.6 280.3 1,840.0 533.3 50 60.00 0.858 0.007

0.7

01/21/09 9,171,503.3 279.8 1,840.0 533.4 50 60.00 2.897 0.025

1.9

01/21/09 9,152,305.2 280.4 1,840.0 527.2 50 60.00 0.758 0.006

0.6

01/21/09 9,155,312.5 280.5 1,840.0 532.4 50 60.00 2.039 0.017

0.6

01/21/09 9,162,580.2 279.9 1,840.0 532.8 50 60.00 0.644 0.005

0.3

01/21/09 9,138,336.2 279.2 1,840.0 531.4 50 60.00 0.644 0.005

0.7

01/21/09 9,174,649.4 280.0 1,840.0 533.5 50 60.00 0.322 0.003

2.2

01/21/09 9,139,739.5 279.9 1,840.0 531.5 50 60.00 0.751 0.006

9.1

01/21/09 9,208,801.8 278.3 1,840.0 530.5 50 60.00 2.383 0.020

0.5

01/21/09 9,178,983.4 277.5 1,840.0 528.8 50 60.00 9.857 0.083

0.4

01/21/09 9,230,224.7 277.3 1,840.0 531.7 50 60.00 0.542 0.005

0.5

01/21/09 9,262,912.8 273.7 1,840.0 533.6 50 60.00 0.433 0.004

0.1

01/21/09 9,309,117.0 260.7 1,840.0 536.3 50 60.00 0.542 0.005

0.1

01/21/09 7,461,669.3 236.0 1,840.0 417.7 39 60.00 0.111 0.001

0.5

01/21/09 5,012,765.0 240.0 1,840.0 223.4 22 60.00 0.140 0.001

0.0

01/21/09 5,143,213.1 257.7 1,840.0 226.4 23 60.00 0.709 0.003

0.0

01/21/09 8,325,659.3 268.4 1,840.0 488.7 48 60.00 0.000 0.000

0.1

01/21/09 8,386,899.3 268.4 1,840.0 496.8 49 60.00 0.000 0.000

2.8

01/21/09 8,546,589.4 271.1 1,840.0 492.4 49 60.00 0.108 0.001

0.2

01/21/09 8,701,542.1 275.4 1,840.0 491.9 49 60.00 3.091 0.024

0.4

01/21/09 9,036,346.2 276.0 1,840.0 510.7 49 60.00 0.221 0.002

0.4

01/21/09 9,072,888.3 274.7 1,840.0 512.8 49 60.00 0.442 0.004

01/21/09 8,999,551.0 274.9 1,840.0 523.4 49 60.00 0.429 0.004
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

14:00 C

15:00 C

16:00 C

17:00 C

18:00 C

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C

03:00 C

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 1.5

1.4

01/24/09 5,251,999.4 240.4 1,840.0 216.9 21 60.00 2.266 0.008

1.5

01/24/09 5,270,096.9 252.6 1,840.0 237.7 22 60.00 1.937 0.007

1.6

01/24/09 6,693,711.6 270.5 1,840.0 331.1 33 60.00 1.893 0.010

1.5

01/23/09 9,103,001.5 276.8 1,840.0 534.3 50 60.00 1.701 0.015

1.2

01/23/09 9,123,603.0 278.3 1,840.0 530.6 50 60.00 1.610 0.014

1.2

01/23/09 9,233,753.8 278.6 1,840.0 532.0 50 60.00 1.300 0.011

1.3

01/23/09 9,234,886.6 278.6 1,840.0 532.0 50 60.00 1.300 0.011

1.3

01/23/09 9,160,029.6 277.6 1,840.0 532.7 50 60.00 1.395 0.012

1.3

01/23/09 9,181,050.0 278.3 1,840.0 533.9 50 60.00 1.395 0.012

1.4

01/23/09 9,204,879.0 280.3 1,840.0 530.3 50 60.00 1.408 0.012

1.5

01/23/09 9,224,905.4 281.0 1,840.0 531.4 50 60.00 1.516 0.013

1.4

01/23/09 9,220,519.0 280.3 1,840.0 531.2 50 60.00 1.625 0.014

1.4

01/23/09 9,173,470.1 278.3 1,840.0 523.5 50 60.00 1.531 0.013

1.5

01/23/09 9,175,861.6 276.1 1,840.0 523.6 50 60.00 1.531 0.013

1.5

01/23/09 9,112,794.6 275.1 1,840.0 529.9 50 60.00 1.610 0.014

1.5

01/23/09 9,134,319.3 275.5 1,840.0 531.2 50 60.00 1.610 0.014

1.8

01/23/09 9,115,388.8 275.3 1,840.0 525.1 50 60.00 1.625 0.014

2.1

01/23/09 9,064,487.8 274.4 1,840.0 527.1 50 60.00 1.931 0.016

2.1

01/23/09 9,013,268.8 272.9 1,840.0 529.0 50 60.00 2.233 0.019

1.9

01/23/09 8,972,615.8 272.6 1,840.0 531.6 50 60.00 2.212 0.019

1.8

01/23/09 9,006,759.5 272.7 1,840.0 528.7 50 60.00 2.020 0.017

3.1

01/23/09 9,012,683.1 275.6 1,840.0 524.1 50 60.00 1.931 0.016

1.8

01/23/09 9,208,041.5 276.5 1,840.0 530.5 50 60.00 3.358 0.028

4.4

01/23/09 9,312,063.2 276.1 1,840.0 536.5 51 60.00 1.950 0.017

1.9

01/23/09 9,037,382.9 276.2 1,840.0 520.6 50 60.00 4.766 0.040

1.4

01/23/09 9,029,087.2 276.4 1,840.0 525.1 49 60.00 2.039 0.017

1.7

01/23/09 9,115,337.4 276.7 1,840.0 530.1 50 60.00 1.502 0.013

1.8

01/22/09 9,117,351.6 277.2 1,840.0 530.2 50 60.00 1.824 0.015

1.9

01/22/09 9,072,788.4 278.0 1,840.0 532.5 50 60.00 1.914 0.016

1.7

01/22/09 9,071,223.1 278.7 1,840.0 527.5 49 60.00 2.039 0.017

1.4

01/22/09 9,201,631.1 278.9 1,840.0 540.1 50 60.00 1.807 0.016

1.7

01/22/09 9,143,999.8 279.3 1,840.0 536.7 50 60.00 1.488 0.013

1.6

01/22/09 9,198,197.1 278.6 1,840.0 534.9 50 60.00 1.824 0.016

1.8

01/22/09 9,128,774.9 277.8 1,840.0 530.9 50 60.00 1.717 0.015

1.9

01/22/09 8,987,239.4 276.3 1,840.0 527.5 50 60.00 1.914 0.016

6.6

01/22/09 9,089,700.7 276.9 1,840.0 528.6 50 60.00 2.039 0.017

01/22/09 9,106,891.4 276.9 1,840.0 529.6 50 60.00 7.082 0.060
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00 C

18:00 C

19:00 C

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00 C

12:00 C

13:00

14:00

15:00 1.4

1.2

01/25/09 8,908,674.9 274.2 1,840.0 542.3 51 60.00 1.435 0.012

1.3

01/25/09 8,864,423.9 274.6 1,840.0 539.5 51 60.00 1.230 0.011

1.3

01/25/09 8,858,857.3 274.9 1,840.0 544.1 51 60.00 1.321 0.011

1.6

01/25/09 8,931,642.7 273.9 1,840.0 543.7 51 60.00 1.333 0.012

1.5

01/25/09 9,001,268.5 269.7 1,840.0 538.1 51 60.00 1.670 0.014

1.3

01/25/09 8,760,663.1 264.0 1,840.0 533.3 51 60.00 1.538 0.013

1.0

01/25/09 8,719,313.7 264.1 1,840.0 535.5 51 60.00 1.321 0.011

0.9

01/25/09 8,750,943.7 264.6 1,840.0 532.7 51 60.00 1.025 0.009

0.9

01/25/09 8,719,945.1 264.4 1,840.0 535.5 51 60.00 0.914 0.008

1.0

01/25/09 8,720,324.3 263.9 1,840.0 535.5 51 60.00 0.914 0.008

2.7

01/25/09 8,720,054.6 264.4 1,840.0 535.5 51 60.00 1.016 0.009

0.9

01/25/09 8,722,702.2 265.1 1,840.0 535.7 51 60.00 2.743 0.024

1.2

01/25/09 8,712,220.6 264.7 1,840.0 530.3 51 60.00 0.923 0.008

0.9

01/25/09 8,715,966.0 263.5 1,840.0 530.5 51 60.00 1.230 0.010

0.8

01/25/09 8,727,489.1 264.3 1,840.0 536.0 51 60.00 0.914 0.008

1.9

01/25/09 8,666,426.6 265.8 1,840.0 532.2 51 60.00 0.813 0.007

2.2

01/24/09 8,714,793.5 269.8 1,840.0 535.2 51 60.00 1.931 0.017

1.8

01/24/09 8,892,907.9 269.5 1,840.0 541.3 51 60.00 2.255 0.020

1.8

01/24/09 8,923,610.8 271.0 1,840.0 538.4 51 60.00 1.862 0.016

3.1

01/24/09 8,919,756.8 272.3 1,840.0 543.0 51 60.00 1.845 0.016

4.4

01/24/09 8,921,116.5 271.7 1,840.0 543.0 51 60.00 3.178 0.028

1.8

01/24/09 8,898,572.5 268.8 1,840.0 541.7 51 60.00 4.511 0.039

1.3

01/24/09 8,984,791.6 266.2 1,840.0 527.4 51 60.00 1.914 0.016

1.6

01/24/09 8,631,246.2 267.2 1,840.0 520.7 51 60.00 1.345 0.011

1.7

01/24/09 8,769,553.2 267.5 1,840.0 519.5 52 60.00 1.685 0.014

1.8

01/24/09 8,767,544.8 266.4 1,840.0 519.4 51 60.00 1.791 0.015

1.6

01/24/09 8,798,419.3 265.7 1,840.0 521.2 51 60.00 1.896 0.016

1.6

01/24/09 8,868,301.2 266.3 1,840.0 520.5 51 60.00 1.701 0.014

1.3

01/24/09 8,977,652.9 265.5 1,840.0 522.1 51 60.00 1.717 0.014

1.3

01/24/09 8,686,662.5 263.1 1,840.0 509.9 51 60.00 1.382 0.011

1.0

01/24/09 8,504,107.3 260.9 1,840.0 503.8 51 60.00 1.369 0.011

1.1

01/24/09 8,606,232.1 261.5 1,840.0 505.1 52 60.00 1.063 0.009

1.4

01/24/09 8,651,159.1 259.1 1,840.0 512.5 51 60.00 1.159 0.009

1.9

01/24/09 8,487,644.0 246.6 1,840.0 521.3 50 60.00 1.422 0.012

3.2

01/24/09 6,693,832.1 228.8 1,840.0 327.4 30 60.00 2.424 0.013

1.9

01/24/09 5,281,304.5 229.3 1,840.0 223.9 20 60.00 4.710 0.017

01/24/09 5,376,932.0 233.3 1,840.0 222.1 20 60.00 2.870 0.010
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 2.8 C

1.2

01/27/09 9,216,118.3 278.7 1,840.0 535.9 50 60.00 3.005 0.026

1.2

01/27/09 9,202,721.3 278.0 1,840.0 530.2 50 60.00 1.300 0.011

0.9

01/27/09 9,160,419.2 276.9 1,840.0 527.7 50 60.00 1.300 0.011

0.8

01/27/09 9,184,004.7 277.4 1,840.0 539.1 50 60.00 0.957 0.008

1.2

01/27/09 9,235,090.1 278.9 1,840.0 542.1 50 60.00 0.850 0.007

1.3

01/26/09 9,267,441.4 279.5 1,840.0 538.9 50 60.00 1.288 0.011

1.3

01/26/09 9,240,561.2 279.1 1,840.0 542.4 50 60.00 1.382 0.012

1.2

01/26/09 9,291,856.2 279.1 1,840.0 545.4 50 60.00 1.382 0.012

1.7

01/26/09 9,276,349.4 278.1 1,840.0 544.5 50 60.00 1.276 0.011

1.9

01/26/09 8,878,079.0 273.7 1,840.0 535.6 50 60.00 1.758 0.015

1.8

01/26/09 8,680,270.4 271.6 1,840.0 528.3 50 60.00 1.948 0.016

1.6

01/26/09 8,677,534.4 272.1 1,840.0 528.2 50 60.00 1.845 0.016

1.7

01/26/09 8,658,173.2 273.0 1,840.0 522.3 50 60.00 1.655 0.014

1.8

01/26/09 8,660,913.5 272.8 1,840.0 522.5 50 60.00 1.758 0.015

1.9

01/26/09 8,661,839.2 272.6 1,840.0 522.5 50 60.00 1.862 0.016

1.8

01/26/09 8,657,538.3 274.3 1,840.0 522.3 50 60.00 1.965 0.016

1.8

01/26/09 8,684,963.7 276.4 1,840.0 523.9 50 60.00 1.862 0.016

1.7

01/26/09 8,880,666.2 276.8 1,840.0 526.1 50 60.00 1.896 0.016

1.3

01/26/09 8,866,521.8 274.4 1,840.0 530.1 50 60.00 1.774 0.015

1.3

01/26/09 8,845,798.9 273.9 1,840.0 524.0 50 60.00 1.369 0.011

1.1

01/26/09 8,852,562.3 273.1 1,840.0 524.4 50 60.00 1.369 0.011

1.3

01/26/09 8,740,400.1 268.0 1,840.0 522.5 50 60.00 1.148 0.010

1.3

01/26/09 8,704,836.5 267.0 1,840.0 534.6 51 60.00 1.321 0.011

2.8

01/26/09 8,691,253.5 265.4 1,840.0 533.7 51 60.00 1.321 0.011

1.1

01/26/09 8,671,869.2 264.5 1,840.0 532.6 51 60.00 2.845 0.024

1.0

01/26/09 8,683,812.3 265.4 1,840.0 533.3 51 60.00 1.118 0.010

1.0

01/26/09 8,769,352.5 266.7 1,840.0 533.8 51 60.00 1.025 0.009

1.2

01/26/09 8,688,043.5 266.5 1,840.0 543.0 51 60.00 0.998 0.009

1.1

01/26/09 8,683,812.3 266.1 1,840.0 542.8 51 60.00 1.198 0.010

1.1

01/25/09 8,669,739.5 267.8 1,840.0 541.9 51 60.00 1.098 0.010

1.3

01/25/09 8,700,704.2 269.5 1,840.0 543.8 51 60.00 1.098 0.010

1.5

01/25/09 8,743,865.2 268.5 1,840.0 541.7 51 60.00 1.309 0.011

1.5

01/25/09 8,708,929.1 265.8 1,840.0 539.6 51 60.00 1.511 0.013

1.3

01/25/09 8,599,629.7 265.8 1,840.0 542.2 51 60.00 1.485 0.013

1.3

01/25/09 8,640,496.1 268.4 1,840.0 540.0 51 60.00 1.298 0.011

1.2

01/25/09 8,754,103.4 271.6 1,840.0 537.6 51 60.00 1.321 0.011

01/25/09 8,824,870.6 273.1 1,840.0 542.0 51 60.00 1.219 0.011
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00 C

15:00 C

16:00 C

17:00 C

18:00 C

19:00

20:00 C

21:00 C

22:00

23:00

00:00

01:00 C

02:00 C

03:00 C

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00 0.9

0.8

01/28/09 9,096,866.7 276.9 1,840.0 534.0 50 60.00 0.957 0.008

0.9

01/28/09 9,136,611.6 276.8 1,840.0 531.3 50 60.00 0.858 0.007

0.8

01/28/09 9,141,879.6 276.2 1,840.0 531.6 50 60.00 0.966 0.008

0.7

01/28/09 9,091,093.1 276.2 1,840.0 528.7 50 60.00 0.858 0.007

0.8

01/28/09 9,061,786.0 276.3 1,840.0 522.0 49 60.00 0.758 0.006

0.9

01/28/09 9,055,336.3 276.2 1,840.0 526.6 50 60.00 0.858 0.007

1.0

01/28/09 9,091,840.2 276.8 1,840.0 528.7 50 60.00 0.966 0.008

0.8

01/28/09 8,921,786.6 276.5 1,840.0 523.7 50 60.00 1.063 0.009

0.8

01/28/09 9,048,711.3 279.2 1,840.0 526.2 50 60.00 0.858 0.007

0.7

01/28/09 9,226,588.4 278.1 1,840.0 531.6 50 60.00 0.867 0.007

0.4

01/28/09 9,242,322.5 274.4 1,840.0 537.4 50 60.00 0.751 0.006

0.0

01/28/09 9,283,070.8 263.5 1,840.0 534.8 50 60.00 0.433 0.004

2.4

01/28/09 7,264,601.0 241.1 1,840.0 402.7 36 60.00 0.000 0.000

2.0

01/28/09 5,422,234.6 239.0 1,840.0 265.2 23 60.00 3.062 0.013

4.3

01/28/09 5,437,628.1 240.3 1,840.0 266.0 23 60.00 2.551 0.011

0.0

01/28/09 5,507,725.1 242.7 1,840.0 263.4 23 60.00 5.610 0.024

0.0

01/28/09 5,373,378.5 249.1 1,840.0 265.7 23 60.00 0.000 0.000

0.6

01/28/09 5,405,675.7 264.3 1,840.0 258.5 23 60.00 0.000 0.000

1.0

01/27/09 7,846,207.0 279.8 1,840.0 434.9 41 60.00 0.675 0.005

1.3

01/27/09 9,172,667.0 281.8 1,840.0 538.4 50 60.00 1.063 0.009

1.7

01/27/09 9,171,155.9 281.3 1,840.0 543.3 50 60.00 1.369 0.012

1.4

01/27/09 9,203,576.0 280.1 1,840.0 540.2 50 60.00 1.807 0.016

1.3

01/27/09 9,209,497.3 281.3 1,840.0 540.5 50 60.00 1.488 0.013

1.2

01/27/09 9,233,045.7 282.3 1,840.0 536.9 50 60.00 1.395 0.012

1.3

01/27/09 9,254,522.6 282.4 1,840.0 538.2 50 60.00 1.288 0.011

2.4

01/27/09 9,207,475.4 280.6 1,840.0 540.4 50 60.00 1.382 0.012

1.3

01/27/09 9,218,119.9 278.5 1,840.0 536.0 50 60.00 2.575 0.022

2.3

01/27/09 9,143,507.3 278.8 1,840.0 536.7 50 60.00 1.382 0.012

1.0

01/27/09 9,160,905.5 280.1 1,840.0 537.7 50 60.00 2.445 0.021

0.1

01/27/09 9,225,768.1 279.8 1,840.0 536.5 50 60.00 1.073 0.009

1.6

01/27/09 9,179,185.0 278.1 1,840.0 538.8 50 60.00 0.106 0.001

0.3

01/27/09 8,993,198.7 280.4 1,840.0 527.9 50 60.00 1.701 0.014

0.0

01/27/09 9,230,713.1 282.5 1,840.0 541.8 50 60.00 0.319 0.003

1.1

01/27/09 9,282,542.8 282.9 1,840.0 539.8 50 60.00 0.000 0.000

1.3

01/27/09 9,201,936.8 282.1 1,840.0 540.1 50 60.00 1.169 0.010

1.2

01/27/09 9,282,455.7 280.6 1,840.0 539.8 50 60.00 1.395 0.012

01/27/09 9,202,025.4 279.6 1,840.0 535.1 50 60.00 1.288 0.011
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00 S S S S S

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C

03:00 C

04:00 C

05:00 C

06:00 0.1

0.0

01/30/09 9,284,934.7 254.1 1,840.0 534.9 50 60.00 0.108 0.001

2.4

01/30/09 6,388,202.8 232.5 1,840.0 340.2 31 60.00 0.000 0.000

2.0

01/30/09 5,282,835.1 233.4 1,840.0 252.7 22 60.00 3.131 0.013

4.4

01/30/09 5,293,561.4 237.3 1,840.0 247.4 22 60.00 2.670 0.011

0.0

01/30/09 5,260,446.4 246.1 1,840.0 245.8 22 60.00 5.874 0.023

0.7

01/30/09 5,358,150.2 259.7 1,840.0 244.6 22 60.00 0.000 0.000

1.1

01/30/09 8,035,198.6 273.4 1,840.0 449.8 43 60.00 0.780 0.006

0.9

01/29/09 9,087,203.2 274.9 1,840.0 538.3 50 60.00 1.159 0.010

0.9

01/29/09 9,048,016.7 275.9 1,840.0 531.1 50 60.00 0.957 0.008

0.7

01/29/09 9,088,774.6 277.1 1,840.0 528.5 50 60.00 0.966 0.008

0.8

01/29/09 9,124,243.6 277.8 1,840.0 525.6 50 60.00 0.758 0.006

0.8

01/29/09 9,048,921.6 277.0 1,840.0 531.1 50 60.00 0.850 0.007

0.8

01/29/09 8,982,367.4 278.4 1,840.0 541.8 50 60.00 0.828 0.007

0.8

01/29/09 9,033,334.3 279.8 1,840.0 540.0 50 60.00 0.835 0.007

0.8

01/29/09 9,022,637.2 280.3 1,840.0 539.4 50 60.00 0.835 0.007

0.8

01/29/09 9,073,468.5 279.4 1,840.0 537.5 50 60.00 0.843 0.007

0.9

01/29/09 9,032,567.7 278.2 1,840.0 540.0 50 60.00 0.835 0.007

0.8

01/29/09 9,082,265.0 277.4 1,840.0 538.0 50 60.00 0.948 0.008

0.7

01/29/09 9,110,337.7 277.3 1,840.0 539.7 50 60.00 0.843 0.007

0.7

01/29/09 9,135,871.8 278.0 1,840.0 536.2 50 60.00 0.744 0.006

0.7

01/29/09 9,149,165.5 277.5 1,840.0 532.0 50 60.00 0.751 0.006

0.7

01/29/09 8,624,000.0 275.7 1,840.0 501.5 50 60.00 0.751 0.006

0.5

01/29/09 9,137,956.1 273.8 1,840.0 536.4 50 60.00 0.744 0.006

0.0

01/29/09 9,170,925.2 267.9 1,840.0 533.3 50 60.00 0.537 0.005

0.0

01/29/09 8,760,510.7 247.6 1,840.0 514.2 46 60.00 0.000 0.000

2.4

01/29/09 5,303,200.1 235.5 1,840.0 268.0 23 60.00 0.000 0.000

0.0

01/29/09 5,219,630.2 236.2 1,840.0 263.8 23 60.00 2.963 0.013

0.0

01/29/09 5,266,806.3 237.7 1,840.0 263.4 23 60.00 0.000 0.000

0.0

01/29/09 5,299,399.7 240.3 1,840.0 264.9 23 60.00 0.000 0.000

0.0

01/29/09 5,331,293.6 245.3 1,840.0 266.5 23 60.00 0.000 0.000

0.6

01/29/09 5,375,380.2 256.0 1,840.0 257.1 23 60.00 0.000 0.000

0.7

01/28/09 7,954,539.5 268.6 1,840.0 441.0 43 60.00 0.675 0.005

0.5

01/28/09 8,970,715.8 272.2 1,840.0 521.7 50 60.00 0.751 0.006

0.8

01/28/09 8,830,510.4 273.6 1,840.0 518.3 50 60.00 0.532 0.004

1.1

01/28/09 8,952,380.9 275.7 1,840.0 530.3 50 60.00 0.843 0.007

1.1

01/28/09 9,039,155.8 275.5 1,840.0 530.6 50 60.00 1.169 0.010

01/28/09 9,094,203.8 276.4 1,840.0 533.8 50 60.00 1.169 0.010
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00 0.4

0.2

01/31/09 9,040,080.2 274.3 1,840.0 520.8 50 60.00 0.433 0.004

0.0

01/31/09 8,190,799.5 263.3 1,840.0 454.1 43 60.00 0.225 0.002

0.0

01/31/09 7,545,265.1 250.1 1,840.0 414.2 38 60.00 0.000 0.000

0.0

01/31/09 5,465,286.3 246.3 1,840.0 246.5 21 60.00 0.000 0.000

0.1

01/31/09 5,406,144.1 253.9 1,840.0 238.0 20 60.00 0.000 0.000

0.7

01/31/09 5,456,646.9 268.9 1,840.0 237.3 21 60.00 0.144 0.001

0.8

01/31/09 8,770,670.3 278.7 1,840.0 495.8 46 60.00 0.773 0.006

0.7

01/31/09 8,985,717.2 277.1 1,840.0 507.9 48 60.00 0.883 0.007

0.6

01/31/09 8,987,179.6 277.1 1,840.0 508.0 48 60.00 0.773 0.006

0.6

01/31/09 8,957,264.4 276.7 1,840.0 506.3 48 60.00 0.662 0.005

0.7

01/31/09 8,983,809.7 275.5 1,840.0 507.8 48 60.00 0.662 0.005

0.6

01/31/09 8,937,398.3 274.7 1,840.0 510.0 48 60.00 0.765 0.006

0.5

01/31/09 8,911,786.1 275.3 1,840.0 508.6 48 60.00 0.656 0.005

0.5

01/31/09 8,971,261.4 275.2 1,840.0 507.1 48 60.00 0.552 0.004

2.6

01/31/09 9,015,578.2 275.2 1,840.0 514.5 48 60.00 0.547 0.004

0.7

01/31/09 9,139,046.6 276.1 1,840.0 526.5 50 60.00 2.816 0.024

0.8

01/31/09 9,144,334.7 275.0 1,840.0 531.7 50 60.00 0.751 0.006

0.4

01/31/09 9,114,753.5 275.0 1,840.0 535.0 50 60.00 0.850 0.007

0.5

01/31/09 9,135,504.6 276.3 1,840.0 536.2 50 60.00 0.425 0.004

0.9

01/31/09 9,198,142.3 276.3 1,840.0 539.9 50 60.00 0.532 0.005

0.9

01/30/09 9,198,299.0 274.8 1,840.0 539.9 50 60.00 0.957 0.008

0.9

01/30/09 9,161,345.9 274.8 1,840.0 537.7 50 60.00 0.957 0.008

0.8

01/30/09 9,130,677.6 275.9 1,840.0 540.9 50 60.00 0.948 0.008

0.7

01/30/09 9,180,064.4 276.7 1,840.0 538.8 50 60.00 0.850 0.007

0.7

01/30/09 9,150,390.2 276.5 1,840.0 537.1 50 60.00 0.744 0.006

0.8

01/30/09 9,161,224.1 274.9 1,840.0 537.7 50 60.00 0.744 0.006

0.8

01/30/09 9,162,277.0 275.2 1,840.0 537.8 50 60.00 0.850 0.007

0.7

01/30/09 9,158,578.1 276.2 1,840.0 537.6 50 60.00 0.850 0.007

0.7

01/30/09 9,236,280.1 276.7 1,840.0 537.1 50 60.00 0.751 0.006

0.7

01/30/09 9,250,819.4 276.1 1,840.0 532.9 50 60.00 0.758 0.006

0.5

01/30/09 9,189,486.0 276.3 1,840.0 534.4 50 60.00 0.751 0.006

0.5

01/30/09 9,220,074.6 276.3 1,840.0 531.2 50 60.00 0.542 0.005

0.6

01/30/09 9,217,714.1 275.0 1,840.0 536.0 50 60.00 0.537 0.005

0.6

01/30/09 9,175,824.4 273.0 1,840.0 533.6 50 60.00 0.644 0.005

0.5

01/30/09 9,171,040.5 272.3 1,840.0 533.3 50 60.00 0.644 0.005

0.3

01/30/09 9,189,680.3 271.1 1,840.0 534.4 50 60.00 0.537 0.005

01/30/09 9,156,175.2 267.4 1,840.0 532.4 50 60.00 0.322 0.003
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00 0.4

0.6

02/02/09 8,849,956.7 281.8 1,840.0 509.8 50 60.00 0.433 0.004

0.8

02/02/09 9,059,524.2 284.0 1,840.0 521.9 50 60.00 0.650 0.005

1.0

02/02/09 9,111,980.7 282.6 1,840.0 529.9 50 60.00 0.858 0.007

2.7

02/02/09 9,109,875.2 280.9 1,840.0 529.8 50 60.00 1.073 0.009

0.7

02/02/09 9,137,447.9 280.2 1,840.0 531.3 50 60.00 2.897 0.025

0.5

02/02/09 9,122,912.8 280.6 1,840.0 525.6 50 60.00 0.758 0.006

0.4

02/02/09 9,129,836.9 280.3 1,840.0 526.0 50 60.00 0.542 0.005

0.4

02/02/09 9,142,956.8 280.4 1,840.0 531.7 50 60.00 0.429 0.004

0.5

02/02/09 9,137,566.5 281.9 1,840.0 531.4 50 60.00 0.429 0.004

0.5

02/01/09 9,189,871.0 282.5 1,840.0 534.4 50 60.00 0.537 0.005

0.5

02/01/09 9,179,498.9 281.6 1,840.0 533.8 50 60.00 0.537 0.005

0.4

02/01/09 9,164,597.2 280.8 1,840.0 537.9 50 60.00 0.532 0.005

0.4

02/01/09 9,188,772.9 281.1 1,840.0 534.4 50 60.00 0.429 0.004

0.3

02/01/09 9,179,500.7 280.1 1,840.0 533.8 50 60.00 0.429 0.004

0.1

02/01/09 9,239,637.8 274.4 1,840.0 537.3 50 60.00 0.322 0.003

0.0

02/01/09 8,414,442.9 252.9 1,840.0 489.3 44 60.00 0.107 0.001

0.0

02/01/09 5,492,216.6 245.3 1,840.0 244.8 20 60.00 0.000 0.000

0.0

02/01/09 5,488,110.7 245.9 1,840.0 244.6 20 60.00 0.000 0.000

0.1

02/01/09 5,492,521.7 247.5 1,840.0 244.8 20 60.00 0.000 0.000

0.1

02/01/09 5,436,371.7 251.9 1,840.0 242.3 20 60.00 0.140 0.001

0.2

02/01/09 5,488,649.4 261.8 1,840.0 241.6 20 60.00 0.142 0.001

0.9

02/01/09 5,767,820.2 276.7 1,840.0 260.2 23 60.00 0.277 0.001

0.8

02/01/09 9,114,879.6 284.9 1,840.0 525.1 49 60.00 0.975 0.008

0.8

02/01/09 9,209,515.6 284.8 1,840.0 535.6 50 60.00 0.858 0.007

0.8

02/01/09 9,206,235.4 284.4 1,840.0 535.3 50 60.00 0.858 0.007

0.6

02/01/09 9,213,821.3 281.8 1,840.0 535.8 50 60.00 0.858 0.007

0.5

02/01/09 9,076,546.4 274.6 1,840.0 522.9 48 60.00 0.650 0.005

2.5

02/01/09 8,337,528.6 270.2 1,840.0 466.7 43 60.00 0.557 0.004

0.2

02/01/09 8,311,926.6 269.3 1,840.0 465.3 43 60.00 2.787 0.021

0.3

02/01/09 8,276,789.1 268.5 1,840.0 458.8 43 60.00 0.225 0.002

1.1

02/01/09 8,305,105.9 269.8 1,840.0 464.9 43 60.00 0.334 0.002

0.3

02/01/09 8,295,949.3 271.1 1,840.0 464.4 43 60.00 1.226 0.009

0.4

02/01/09 8,327,051.3 271.6 1,840.0 466.1 43 60.00 0.334 0.002

0.5

01/31/09 8,364,906.5 271.3 1,840.0 463.7 43 60.00 0.450 0.003

0.6

01/31/09 8,253,250.8 274.5 1,840.0 457.5 43 60.00 0.563 0.004

0.4

01/31/09 9,086,438.3 278.9 1,840.0 518.5 49 60.00 0.656 0.005

01/31/09 9,156,371.1 278.0 1,840.0 522.5 50 60.00 0.437 0.004
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

09:00

10:00

11:00

12:00 S IM S S S

13:00 M

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00

03:00

04:00 C

05:00 C

06:00

07:00

08:00

09:00

10:00

11:00 C

12:00 C

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00 1.6

1.7

02/03/09 10,505,917.3 297.0 1,840.0 639.5 60 60.00 1.640 0.017

1.7

02/03/09 10,505,574.0 296.4 1,840.0 639.5 60 60.00 1.743 0.018

1.8

02/03/09 10,462,903.2 296.8 1,840.0 636.9 60 60.00 1.743 0.018

1.8

02/03/09 10,458,913.7 294.9 1,840.0 642.3 60 60.00 1.829 0.019

1.9

02/03/09 10,332,992.1 292.9 1,840.0 640.2 60 60.00 1.813 0.019

1.7

02/03/09 10,318,455.0 292.3 1,840.0 639.3 60 60.00 1.914 0.020

1.7

02/03/09 10,337,876.7 292.5 1,840.0 640.5 60 60.00 1.712 0.018

1.6

02/03/09 10,368,793.9 292.2 1,840.0 642.4 60 60.00 1.712 0.018

1.6

02/03/09 10,391,429.1 291.5 1,840.0 643.8 60 60.00 1.611 0.017

2.5

02/03/09 10,303,489.7 290.1 1,840.0 638.3 60 60.00 1.611 0.016

0.9

02/03/09 10,341,475.8 290.1 1,840.0 640.7 60 60.00 2.518 0.026

0.8

02/03/09 10,246,693.7 287.0 1,840.0 623.7 58 60.00 0.923 0.009

0.8

02/03/09 9,738,205.2 283.1 1,840.0 582.2 55 60.00 0.835 0.008

0.8

02/03/09 9,433,230.7 278.1 1,840.0 558.8 53 60.00 0.843 0.008

0.8

02/03/09 9,042,502.1 276.7 1,840.0 530.8 50 60.00 0.850 0.007

0.8

02/03/09 9,088,902.6 277.4 1,840.0 533.5 50 60.00 0.850 0.007

2.7

02/03/09 9,092,669.3 276.7 1,840.0 528.8 50 60.00 0.858 0.007

0.7

02/03/09 9,053,197.0 275.1 1,840.0 526.5 50 60.00 2.897 0.024

0.6

02/03/09 9,090,607.3 274.7 1,840.0 523.7 50 60.00 0.758 0.006

0.6

02/03/09 9,049,828.1 275.5 1,840.0 521.4 50 60.00 0.650 0.005

0.6

02/03/09 9,139,243.1 275.7 1,840.0 531.5 50 60.00 0.644 0.005

0.6

02/03/09 9,118,437.4 275.5 1,840.0 530.2 50 60.00 0.644 0.005

0.7

02/02/09 9,125,092.8 276.9 1,840.0 530.6 50 60.00 0.644 0.005

0.7

02/02/09 9,115,090.4 278.4 1,840.0 530.1 50 60.00 0.751 0.006

0.8

02/02/09 9,161,217.5 278.6 1,840.0 527.8 50 60.00 0.758 0.006

0.8

02/02/09 9,175,360.9 278.8 1,840.0 533.5 50 60.00 0.858 0.007

0.7

02/02/09 9,144,227.3 281.0 1,840.0 531.7 50 60.00 0.858 0.007

0.8

02/02/09 9,231,065.7 283.3 1,840.0 531.8 50 60.00 0.758 0.006

0.8

02/02/09 9,228,242.1 282.4 1,840.0 531.6 50 60.00 0.867 0.007

0.6

02/02/09 9,246,465.2 280.7 1,840.0 532.6 50 60.00 0.867 0.007

0.5

02/02/09 9,257,943.4 281.1 1,840.0 533.3 50 60.00 0.650 0.006

0.4

02/02/09 9,291,481.6 281.1 1,840.0 530.2 50 60.00 0.547 0.005

0.1

02/02/09 9,280,380.1 277.7 1,840.0 529.6 50 60.00 0.437 0.004

0.7

02/02/09 7,195,000.0 0.0 1,840.0 394.9 39 60.00 0.114 0.001

0.5

02/02/09 8,069,571.9 276.1 1,840.0 421.0 41 60.00 0.837 0.006

0.3

02/02/09 8,949,845.5 278.5 1,840.0 505.9 50 60.00 0.552 0.004

02/02/09 8,874,481.3 279.5 1,840.0 506.4 50 60.00 0.328 0.003
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00 C

16:00 C

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00 1.1

1.3

02/05/09 9,281,174.8 270.4 1,840.0 529.6 50 60.00 1.203 0.010

1.2

02/05/09 9,281,719.8 269.1 1,840.0 529.7 50 60.00 1.422 0.012

1.0

02/05/09 9,287,494.3 269.5 1,840.0 530.0 50 60.00 1.312 0.011

0.8

02/05/09 9,249,876.9 268.7 1,840.0 532.9 50 60.00 1.083 0.009

0.7

02/05/09 8,967,804.1 262.7 1,840.0 511.8 47 60.00 0.875 0.007

2.8

02/05/09 7,861,274.8 262.3 1,840.0 423.0 40 60.00 0.812 0.005

1.3

02/05/09 8,825,583.1 271.6 1,840.0 494.1 47 60.00 3.121 0.025

1.3

02/05/09 9,733,083.4 276.3 1,840.0 560.7 54 60.00 1.408 0.013

1.5

02/05/09 9,797,456.4 278.0 1,840.0 564.4 54 60.00 1.408 0.013

1.7

02/05/09 9,730,925.4 279.8 1,840.0 571.2 54 60.00 1.595 0.015

1.7

02/05/09 10,503,594.8 283.0 1,840.0 628.0 60 60.00 1.774 0.018

1.6

02/04/09 10,443,597.4 284.2 1,840.0 635.7 60 60.00 1.743 0.018

1.6

02/04/09 10,504,864.5 284.5 1,840.0 639.4 60 60.00 1.640 0.017

1.7

02/04/09 10,472,261.4 284.1 1,840.0 637.4 60 60.00 1.640 0.017

1.4

02/04/09 10,453,668.0 283.6 1,840.0 636.3 60 60.00 1.743 0.018

1.1

02/04/09 10,451,430.7 284.5 1,840.0 636.1 60 60.00 1.435 0.015

0.5

02/04/09 10,481,104.2 281.9 1,840.0 643.7 60 60.00 1.118 0.012

0.2

02/04/09 10,039,309.9 265.2 1,840.0 616.5 56 60.00 0.508 0.005

1.2

02/04/09 6,459,014.1 256.2 1,840.0 340.5 31 60.00 0.237 0.001

1.5

02/04/09 7,014,560.1 270.9 1,840.0 366.0 34 60.00 1.435 0.008

1.8

02/04/09 9,285,182.8 284.1 1,840.0 545.0 51 60.00 1.595 0.014

1.9

02/04/09 10,550,691.6 290.2 1,840.0 642.2 60 60.00 1.845 0.019

2.2

02/04/09 10,531,901.3 290.7 1,840.0 641.1 60 60.00 1.948 0.020

1.9

02/04/09 10,446,026.7 289.4 1,840.0 641.5 60 60.00 2.235 0.023

1.8

02/04/09 10,423,740.2 290.1 1,840.0 634.5 60 60.00 1.948 0.020

1.9

02/04/09 10,450,649.9 291.6 1,840.0 641.8 60 60.00 1.829 0.019

2.1

02/04/09 10,526,810.4 291.9 1,840.0 635.1 60 60.00 1.965 0.020

2.0

02/04/09 10,453,516.0 291.5 1,840.0 636.3 60 60.00 2.153 0.022

1.9

02/04/09 10,480,784.7 290.6 1,840.0 638.0 60 60.00 2.050 0.021

3.0

02/04/09 10,466,692.3 291.3 1,840.0 631.4 60 60.00 1.965 0.020

1.7

02/04/09 10,474,365.4 291.7 1,840.0 631.9 60 60.00 3.103 0.031

1.7

02/04/09 10,490,947.7 291.4 1,840.0 627.2 60 60.00 1.774 0.018

1.3

02/04/09 10,486,509.2 292.1 1,840.0 626.9 60 60.00 1.774 0.018

1.4

02/04/09 10,466,423.9 293.6 1,840.0 631.4 60 60.00 1.345 0.014

1.8

02/04/09 10,504,067.0 294.5 1,840.0 633.7 60 60.00 1.448 0.015

1.8

02/03/09 10,474,601.7 294.6 1,840.0 631.9 60 60.00 1.862 0.019

02/03/09 10,468,749.9 296.2 1,840.0 637.2 60 60.00 1.845 0.019
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C C

03:00 C

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00 0.0

0.0

02/06/09 5,517,691.4 238.3 1,840.0 266.9 23 60.00 0.000 0.000

0.0

02/06/09 5,438,297.7 240.1 1,840.0 266.0 23 60.00 0.000 0.000

0.0

02/06/09 5,429,432.8 243.5 1,840.0 265.5 23 60.00 0.000 0.000

0.0

02/06/09 5,666,669.5 245.1 1,840.0 292.6 26 60.00 0.000 0.000

0.0

02/06/09 5,609,620.5 244.7 1,840.0 292.7 26 60.00 0.000 0.000

0.0

02/06/09 5,500,070.6 245.2 1,840.0 289.9 26 60.00 0.000 0.000

0.0

02/06/09 5,851,437.5 247.4 1,840.0 289.4 26 60.00 0.000 0.000

0.0

02/06/09 5,933,646.5 248.4 1,840.0 293.5 26 60.00 0.000 0.000

0.0

02/06/09 5,989,166.8 252.0 1,840.0 279.9 24 60.00 0.000 0.000

0.4

02/06/09 5,644,589.0 261.7 1,840.0 279.2 24 60.00 0.000 0.000

0.5

02/06/09 7,564,709.4 272.3 1,840.0 394.7 38 60.00 0.478 0.003

0.5

02/06/09 8,692,944.1 273.7 1,840.0 481.9 45 60.00 0.563 0.004

0.6

02/06/09 8,670,342.6 272.5 1,840.0 480.6 45 60.00 0.563 0.004

0.5

02/06/09 8,615,045.4 270.3 1,840.0 477.6 45 60.00 0.675 0.005

0.2

02/06/09 8,874,368.8 270.6 1,840.0 491.9 47 60.00 0.563 0.004

0.0

02/06/09 9,255,852.8 265.1 1,840.0 523.2 50 60.00 0.221 0.002

0.0

02/06/09 8,267,826.0 245.2 1,840.0 467.3 43 60.00 0.000 0.000

0.0

02/06/09 5,567,723.8 236.9 1,840.0 281.4 24 60.00 0.000 0.000

2.4

02/06/09 5,432,558.1 236.8 1,840.0 265.7 23 60.00 0.000 0.000

2.0

02/06/09 5,463,183.6 236.0 1,840.0 267.2 23 60.00 3.062 0.013

4.4

02/06/09 5,487,360.1 234.5 1,840.0 265.4 23 60.00 2.580 0.011

0.0

02/06/09 5,348,955.0 233.9 1,840.0 267.4 23 60.00 5.491 0.023

0.0

02/06/09 5,359,913.4 234.5 1,840.0 268.0 23 60.00 0.000 0.000

0.0

02/06/09 5,331,371.1 236.5 1,840.0 266.5 23 60.00 0.000 0.000

0.0

02/05/09 5,355,050.8 242.1 1,840.0 264.8 23 60.00 0.000 0.000

0.4

02/05/09 5,485,884.8 254.3 1,840.0 259.4 23 60.00 0.000 0.000

0.6

02/05/09 7,641,155.3 266.4 1,840.0 394.5 39 60.00 0.483 0.003

0.0

02/05/09 9,258,614.7 261.1 1,840.0 528.4 50 60.00 0.656 0.006

0.0

02/05/09 7,444,154.2 246.6 1,840.0 400.5 37 60.00 0.000 0.000

0.0

02/05/09 6,449,383.6 245.4 1,840.0 315.4 29 60.00 0.000 0.000

0.1

02/05/09 6,399,803.9 246.3 1,840.0 313.0 29 60.00 0.000 0.000

0.5

02/05/09 6,441,975.5 250.4 1,840.0 311.6 29 60.00 0.129 0.001

1.1

02/05/09 7,051,215.5 260.4 1,840.0 337.2 32 60.00 0.652 0.004

1.5

02/05/09 8,583,452.5 269.2 1,840.0 471.1 45 60.00 1.250 0.009

1.2

02/05/09 9,221,873.3 270.2 1,840.0 531.3 50 60.00 1.625 0.014

1.2

02/05/09 9,322,700.5 271.0 1,840.0 532.0 50 60.00 1.312 0.011

02/05/09 9,304,597.5 271.3 1,840.0 531.0 50 60.00 1.312 0.011
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00 0.0

0.0

02/08/09 5,155,642.8 231.5 1,840.0 280.2 24 60.00 0.000 0.000

0.0

02/08/09 5,135,634.0 230.4 1,840.0 276.3 24 60.00 0.000 0.000

0.0

02/08/09 5,107,261.3 231.0 1,840.0 277.6 24 60.00 0.000 0.000

0.0

02/08/09 5,124,643.0 230.9 1,840.0 278.5 24 60.00 0.000 0.000

0.0

02/08/09 5,132,458.5 230.6 1,840.0 276.1 24 60.00 0.000 0.000

0.0

02/08/09 5,105,103.4 230.9 1,840.0 277.4 24 60.00 0.000 0.000

0.0

02/08/09 5,079,368.4 232.1 1,840.0 276.0 24 60.00 0.000 0.000

0.0

02/08/09 5,057,303.2 232.9 1,840.0 269.3 23 60.00 0.000 0.000

0.0

02/08/09 5,089,126.8 234.3 1,840.0 268.3 23 60.00 0.000 0.000

0.2

02/08/09 5,026,963.0 238.4 1,840.0 265.0 23 60.00 0.000 0.000

0.0

02/08/09 5,446,448.2 242.5 1,840.0 266.4 23 60.00 0.255 0.001

0.0

02/08/09 5,479,423.5 245.0 1,840.0 273.9 23 60.00 0.000 0.000

0.0

02/08/09 5,436,707.3 248.2 1,840.0 268.9 23 60.00 0.000 0.000

0.3

02/07/09 5,520,518.0 255.5 1,840.0 270.0 23 60.00 0.000 0.000

0.8

02/07/09 5,751,511.2 268.3 1,840.0 275.1 25 60.00 0.391 0.002

0.7

02/07/09 9,149,610.3 276.8 1,840.0 522.1 50 60.00 0.875 0.007

0.5

02/07/09 9,247,339.2 277.2 1,840.0 537.7 51 60.00 0.751 0.006

0.1

02/07/09 9,307,361.8 275.8 1,840.0 541.2 51 60.00 0.537 0.005

0.0

02/07/09 9,346,176.0 269.5 1,840.0 543.5 51 60.00 0.107 0.001

0.0

02/07/09 8,016,188.5 250.8 1,840.0 461.8 42 60.00 0.000 0.000

0.0

02/07/09 5,518,414.6 247.5 1,840.0 281.9 26 60.00 0.000 0.000

0.0

02/07/09 5,682,243.7 247.9 1,840.0 296.5 26 60.00 0.000 0.000

0.0

02/07/09 5,671,155.9 247.2 1,840.0 292.8 26 60.00 0.000 0.000

0.0

02/07/09 5,626,277.2 247.7 1,840.0 293.5 26 60.00 0.000 0.000

0.0

02/07/09 5,652,170.1 247.9 1,840.0 291.8 26 60.00 0.000 0.000

0.0

02/07/09 5,663,299.9 245.7 1,840.0 292.4 26 60.00 0.000 0.000

0.0

02/07/09 5,623,277.3 242.8 1,840.0 275.0 24 60.00 0.000 0.000

0.0

02/07/09 5,516,109.9 241.0 1,840.0 263.8 23 60.00 0.000 0.000

0.0

02/07/09 5,495,256.8 240.5 1,840.0 265.8 23 60.00 0.000 0.000

0.0

02/07/09 5,489,169.8 241.4 1,840.0 262.5 23 60.00 0.000 0.000

0.0

02/07/09 5,554,560.4 241.6 1,840.0 262.7 23 60.00 0.000 0.000

0.0

02/07/09 5,552,929.4 240.2 1,840.0 262.6 23 60.00 0.000 0.000

0.0

02/07/09 5,564,864.2 238.1 1,840.0 266.2 23 60.00 0.000 0.000

0.0

02/07/09 5,474,787.9 237.4 1,840.0 264.8 23 60.00 0.000 0.000

0.0

02/07/09 5,508,969.6 238.8 1,840.0 263.5 23 60.00 0.000 0.000

0.0

02/07/09 5,523,882.8 239.1 1,840.0 267.2 23 60.00 0.000 0.000

02/07/09 5,534,566.4 238.7 1,840.0 267.7 23 60.00 0.000 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 0.7

0.9

02/10/09 9,283,840.8 278.5 1,840.0 529.8 50 60.00 0.765 0.006

1.0

02/10/09 9,337,956.7 278.5 1,840.0 527.8 50 60.00 0.994 0.008

1.0

02/09/09 9,296,051.9 277.8 1,840.0 530.5 50 60.00 1.093 0.009

0.8

02/09/09 9,192,501.0 278.3 1,840.0 524.6 50 60.00 1.093 0.009

0.7

02/09/09 9,288,556.8 278.4 1,840.0 530.1 50 60.00 0.875 0.007

0.5

02/09/09 9,313,297.7 278.7 1,840.0 531.4 50 60.00 0.765 0.007

0.5

02/09/09 9,247,361.4 279.9 1,840.0 527.7 50 60.00 0.547 0.005

0.6

02/09/09 9,272,295.3 279.8 1,840.0 529.1 50 60.00 0.547 0.005

0.5

02/09/09 9,504,097.6 277.5 1,840.0 532.0 50 60.00 0.669 0.006

0.4

02/09/09 9,083,300.1 274.9 1,840.0 518.3 50 60.00 0.547 0.005

0.5

02/09/09 9,094,696.5 275.6 1,840.0 519.0 50 60.00 0.437 0.004

0.8

02/09/09 9,021,399.0 276.4 1,840.0 519.7 50 60.00 0.542 0.005

0.5

02/09/09 9,393,777.8 275.6 1,840.0 531.0 50 60.00 0.883 0.007

0.5

02/09/09 9,030,320.7 275.0 1,840.0 515.3 49 60.00 0.547 0.005

0.6

02/09/09 9,050,616.5 276.8 1,840.0 521.4 50 60.00 0.542 0.005

0.8

02/09/09 9,099,726.1 277.5 1,840.0 534.1 50 60.00 0.638 0.005

0.6

02/09/09 9,175,198.4 276.2 1,840.0 538.5 50 60.00 0.850 0.007

0.3

02/09/09 9,210,532.8 275.7 1,840.0 540.6 50 60.00 0.638 0.006

0.1

02/09/09 9,273,926.1 272.7 1,840.0 534.3 50 60.00 0.325 0.003

0.0

02/09/09 9,383,037.2 258.7 1,840.0 540.5 50 60.00 0.108 0.001

0.0

02/09/09 6,653,639.6 234.5 1,840.0 376.1 33 60.00 0.000 0.000

0.0

02/09/09 5,043,484.0 232.4 1,840.0 260.4 22 60.00 0.000 0.000

0.0

02/09/09 5,044,062.8 232.4 1,840.0 257.7 22 60.00 0.000 0.000

0.0

02/09/09 5,041,350.2 233.5 1,840.0 257.5 22 60.00 0.000 0.000

0.0

02/09/09 5,036,829.6 237.5 1,840.0 260.1 22 60.00 0.000 0.000

0.0

02/09/09 5,094,367.7 244.3 1,840.0 260.2 22 60.00 0.000 0.000

0.1

02/08/09 5,099,659.6 256.6 1,840.0 263.3 23 60.00 0.000 0.000

0.7

02/08/09 5,869,358.9 272.8 1,840.0 287.1 26 60.00 0.128 0.001

0.5

02/08/09 9,111,842.3 279.9 1,840.0 529.9 49 60.00 0.751 0.006

0.4

02/08/09 9,256,393.3 278.1 1,840.0 538.3 50 60.00 0.537 0.005

0.2

02/08/09 9,265,006.1 275.7 1,840.0 538.8 50 60.00 0.429 0.004

0.0

02/08/09 9,277,915.7 269.1 1,840.0 539.5 50 60.00 0.215 0.002

0.0

02/08/09 8,381,110.6 243.0 1,840.0 487.4 43 60.00 0.000 0.000

0.0

02/08/09 5,084,541.8 230.9 1,840.0 276.4 24 60.00 0.000 0.000

0.0

02/08/09 5,112,483.5 231.4 1,840.0 277.8 24 60.00 0.000 0.000

0.0

02/08/09 5,096,501.0 232.6 1,840.0 277.0 24 60.00 0.000 0.000

02/08/09 5,126,559.9 232.5 1,840.0 278.6 24 60.00 0.000 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 C

12:00 C

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00 0.9

1.0

02/11/09 9,271,648.8 283.5 1,840.0 529.1 50 60.00 0.984 0.008

0.9

02/11/09 9,213,917.0 282.0 1,840.0 525.8 50 60.00 1.093 0.009

0.8

02/11/09 9,251,846.9 280.6 1,840.0 533.0 50 60.00 0.975 0.008

0.6

02/11/09 9,273,372.8 279.8 1,840.0 534.2 50 60.00 0.867 0.007

0.5

02/11/09 9,212,221.6 280.1 1,840.0 530.7 50 60.00 0.650 0.006

0.4

02/11/09 9,211,567.9 278.6 1,840.0 530.7 50 60.00 0.542 0.005

0.1

02/11/09 9,223,691.3 272.6 1,840.0 531.4 50 60.00 0.433 0.004

0.0

02/11/09 9,210,277.0 254.3 1,840.0 535.6 50 60.00 0.107 0.001

0.0

02/11/09 5,933,354.1 236.3 1,840.0 293.4 25 60.00 0.000 0.000

0.0

02/11/09 5,109,129.1 236.3 1,840.0 230.5 19 60.00 0.000 0.000

0.0

02/11/09 5,099,151.0 237.1 1,840.0 230.0 19 60.00 0.000 0.000

0.0

02/11/09 5,105,823.9 238.8 1,840.0 227.5 19 60.00 0.000 0.000

0.0

02/11/09 5,168,067.8 241.7 1,840.0 233.1 19 60.00 0.000 0.000

0.0

02/11/09 5,138,899.5 243.4 1,840.0 234.6 19 60.00 0.000 0.000

0.0

02/11/09 5,120,283.5 247.5 1,840.0 233.7 19 60.00 0.000 0.000

0.2

02/10/09 5,078,192.1 256.6 1,840.0 231.8 19 60.00 0.000 0.000

0.9

02/10/09 5,285,920.7 270.8 1,840.0 224.1 19 60.00 0.294 0.001

1.1

02/10/09 8,458,579.2 283.1 1,840.0 468.9 44 60.00 1.013 0.008

1.0

02/10/09 9,385,934.3 283.7 1,840.0 535.6 50 60.00 1.203 0.010

1.1

02/10/09 9,242,732.2 283.4 1,840.0 522.4 50 60.00 1.104 0.009

1.1

02/10/09 9,296,516.6 283.9 1,840.0 530.5 50 60.00 1.203 0.010

1.4

02/10/09 9,266,533.2 283.0 1,840.0 528.8 50 60.00 1.203 0.010

1.3

02/10/09 9,278,954.5 282.2 1,840.0 524.5 50 60.00 1.546 0.013

1.1

02/10/09 9,322,000.4 283.0 1,840.0 532.0 50 60.00 1.422 0.012

1.2

02/10/09 9,365,615.7 282.9 1,840.0 534.5 50 60.00 1.203 0.010

1.2

02/10/09 9,293,671.4 280.7 1,840.0 525.3 50 60.00 1.325 0.011

1.2

02/10/09 9,328,745.4 280.4 1,840.0 527.3 50 60.00 1.325 0.011

1.1

02/10/09 9,324,411.7 282.6 1,840.0 527.0 50 60.00 1.325 0.011

1.0

02/10/09 9,344,331.2 282.2 1,840.0 528.1 50 60.00 1.214 0.010

1.2

02/10/09 9,300,123.3 280.7 1,840.0 525.7 50 60.00 1.104 0.009

1.2

02/10/09 9,334,097.3 278.3 1,840.0 527.6 50 60.00 1.325 0.011

1.0

02/10/09 9,294,780.2 278.0 1,840.0 525.4 50 60.00 1.325 0.011

0.9

02/10/09 9,317,563.5 279.4 1,840.0 526.7 50 60.00 1.104 0.009

1.0

02/10/09 9,260,206.0 279.8 1,840.0 523.4 50 60.00 0.994 0.008

1.1

02/10/09 9,319,138.6 279.2 1,840.0 526.7 50 60.00 1.104 0.009

1.0

02/10/09 9,278,608.8 277.5 1,840.0 524.5 50 60.00 1.214 0.010

02/10/09 9,258,361.1 277.8 1,840.0 523.3 50 60.00 1.104 0.009
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C C

03:00 0.1 C

4.7

02/13/09 5,459,116.9 235.1 1,840.0 240.3 20 60.00 0.142 0.001

0.0

02/13/09 5,254,572.5 238.5 1,840.0 234.2 19 60.00 6.581 0.025

0.0

02/13/09 5,258,903.1 245.6 1,840.0 234.4 19 60.00 0.000 0.000

0.4

02/13/09 5,194,087.9 260.1 1,840.0 231.5 19 60.00 0.000 0.000

0.9

02/12/09 7,064,500.3 276.9 1,840.0 345.6 33 60.00 0.510 0.003

1.1

02/12/09 9,280,374.7 284.4 1,840.0 544.7 51 60.00 0.957 0.008

1.1

02/12/09 9,852,876.8 286.9 1,840.0 589.0 55 60.00 1.148 0.011

1.1

02/12/09 9,838,561.4 289.2 1,840.0 588.2 55 60.00 1.148 0.011

1.1

02/12/09 9,860,346.3 290.0 1,840.0 589.5 55 60.00 1.148 0.011

1.0

02/12/09 9,909,679.3 287.5 1,840.0 587.1 55 60.00 1.159 0.011

1.1

02/12/09 9,396,396.5 281.0 1,840.0 546.4 51 60.00 1.073 0.009

1.1

02/12/09 9,108,159.7 278.3 1,840.0 524.7 50 60.00 1.191 0.010

0.8

02/12/09 9,043,163.5 278.1 1,840.0 511.1 50 60.00 1.214 0.010

0.9

02/12/09 9,028,266.8 278.0 1,840.0 505.4 50 60.00 0.892 0.007

0.8

02/12/09 9,023,034.4 278.2 1,840.0 505.1 50 60.00 1.003 0.008

0.8

02/12/09 9,027,283.3 278.4 1,840.0 505.3 50 60.00 0.892 0.007

0.7

02/12/09 9,069,360.4 277.9 1,840.0 512.6 50 60.00 0.883 0.007

0.6

02/12/09 9,037,706.3 276.9 1,840.0 530.5 50 60.00 0.744 0.006

0.3

02/12/09 9,068,430.7 275.7 1,840.0 532.3 50 60.00 0.638 0.005

0.1

02/12/09 9,206,090.6 273.3 1,840.0 535.3 50 60.00 0.322 0.003

0.0

02/12/09 9,311,316.6 260.6 1,840.0 541.5 50 60.00 0.107 0.001

0.0

02/12/09 6,681,957.2 243.1 1,840.0 370.4 33 60.00 0.000 0.000

0.0

02/12/09 5,680,790.3 243.9 1,840.0 293.3 26 60.00 0.000 0.000

0.0

02/12/09 5,704,133.3 245.7 1,840.0 294.5 26 60.00 0.000 0.000

0.0

02/12/09 5,704,204.5 249.7 1,840.0 291.4 26 60.00 0.000 0.000

0.0

02/12/09 5,710,473.7 260.4 1,840.0 291.7 26 60.00 0.000 0.000

0.5

02/12/09 6,209,920.7 273.2 1,840.0 317.3 30 60.00 0.000 0.000

0.8

02/12/09 9,221,558.2 279.9 1,840.0 531.3 50 60.00 0.542 0.005

0.8

02/11/09 9,216,099.1 279.2 1,840.0 530.9 50 60.00 0.867 0.007

0.8

02/11/09 9,206,803.2 279.8 1,840.0 530.4 50 60.00 0.867 0.007

0.8

02/11/09 9,195,799.3 281.2 1,840.0 529.8 50 60.00 0.867 0.007

0.7

02/11/09 9,223,574.8 281.9 1,840.0 526.4 50 60.00 0.875 0.007

0.7

02/11/09 9,217,155.4 283.3 1,840.0 526.0 50 60.00 0.765 0.006

0.8

02/11/09 9,255,323.4 286.1 1,840.0 528.1 50 60.00 0.765 0.006

0.8

02/11/09 9,289,146.7 287.2 1,840.0 530.1 50 60.00 0.875 0.007

0.9

02/11/09 9,267,932.2 286.8 1,840.0 528.9 50 60.00 0.875 0.007

02/11/09 9,265,789.9 285.1 1,840.0 533.8 50 60.00 0.975 0.008
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00 0.5

0.7

02/14/09 6,325,086.8 240.0 1,840.0 340.3 30 60.00 0.580 0.003

1.0

02/14/09 5,298,146.3 240.2 1,840.0 256.3 22 60.00 0.903 0.004

1.2

02/14/09 5,126,399.4 247.9 1,840.0 245.2 22 60.00 1.305 0.005

1.5

02/14/09 5,182,080.5 264.8 1,840.0 233.8 22 60.00 1.660 0.006

1.5

02/14/09 8,638,265.3 278.0 1,840.0 492.9 46 60.00 1.640 0.013

1.4

02/14/09 9,094,491.0 277.1 1,840.0 533.8 50 60.00 1.595 0.014

0.8

02/14/09 9,124,952.1 273.3 1,840.0 535.6 50 60.00 1.488 0.013

0.7

02/14/09 8,846,177.7 254.7 1,840.0 533.6 48 60.00 0.828 0.007

0.6

02/14/09 5,591,480.7 239.4 1,840.0 279.6 24 60.00 0.874 0.004

0.7

02/14/09 5,342,205.2 238.9 1,840.0 258.4 22 60.00 0.774 0.003

0.7

02/14/09 5,335,384.8 238.6 1,840.0 258.1 22 60.00 0.903 0.004

0.7

02/14/09 5,325,781.5 238.4 1,840.0 257.6 22 60.00 0.903 0.004

0.6

02/14/09 5,335,205.8 237.6 1,840.0 258.1 22 60.00 0.903 0.004

1.0

02/14/09 5,380,608.6 235.9 1,840.0 257.4 22 60.00 0.783 0.003

0.7

02/14/09 5,221,886.4 235.9 1,840.0 241.2 22 60.00 1.351 0.005

0.8

02/14/09 5,146,251.7 239.2 1,840.0 246.1 22 60.00 0.913 0.004

0.6

02/14/09 5,174,144.8 247.9 1,840.0 244.6 22 60.00 1.056 0.004

0.6

02/13/09 5,184,162.5 264.5 1,840.0 239.5 22 60.00 0.810 0.003

0.8

02/13/09 8,179,188.3 280.0 1,840.0 444.5 42 60.00 0.689 0.005

0.9

02/13/09 9,236,631.8 281.8 1,840.0 537.2 50 60.00 0.858 0.007

0.8

02/13/09 9,248,950.3 283.5 1,840.0 537.8 50 60.00 0.966 0.008

0.8

02/13/09 9,259,436.9 283.4 1,840.0 538.4 50 60.00 0.858 0.007

1.1

02/13/09 9,223,106.6 281.1 1,840.0 536.3 50 60.00 0.858 0.007

1.0

02/13/09 9,163,282.6 278.0 1,840.0 537.8 50 60.00 1.169 0.010

1.0

02/13/09 9,116,656.3 278.1 1,840.0 535.1 50 60.00 1.063 0.009

0.9

02/13/09 9,146,879.3 279.9 1,840.0 526.9 50 60.00 1.083 0.009

0.9

02/13/09 9,177,900.5 279.9 1,840.0 523.7 50 60.00 0.984 0.008

1.1

02/13/09 9,191,156.4 278.7 1,840.0 539.5 50 60.00 0.957 0.008

0.8

02/13/09 9,183,608.6 276.8 1,840.0 534.1 50 60.00 1.180 0.010

0.7

02/13/09 9,159,493.4 277.4 1,840.0 532.6 50 60.00 0.858 0.007

0.8

02/13/09 9,171,079.6 276.8 1,840.0 528.3 50 60.00 0.758 0.006

0.5

02/13/09 9,151,231.9 274.4 1,840.0 527.2 50 60.00 0.867 0.007

0.2

02/13/09 9,153,210.1 270.1 1,840.0 542.2 50 60.00 0.527 0.005

0.0

02/13/09 9,163,354.0 261.7 1,840.0 542.8 50 60.00 0.211 0.002

0.0

02/13/09 7,672,858.8 241.3 1,840.0 437.9 40 60.00 0.000 0.000

0.0

02/13/09 5,749,397.8 236.3 1,840.0 293.7 26 60.00 0.000 0.000

02/13/09 5,751,205.0 234.8 1,840.0 290.7 26 60.00 0.000 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00 C

10:00 C

11:00 C

12:00 C

13:00 C

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C 0.5 C

0.4

02/16/09 5,338,966.5 237.0 1,840.0 258.2 22 60.00 0.645 0.003

0.4

02/16/09 5,329,640.5 238.2 1,840.0 257.8 22 60.00 0.516 0.002

0.5

02/16/09 5,323,475.8 241.0 1,840.0 254.6 22 60.00 0.522 0.002

0.4

02/16/09 5,342,757.8 248.9 1,840.0 258.4 22 60.00 0.645 0.003

1.5

02/16/09 5,372,240.9 262.1 1,840.0 256.9 22 60.00 0.522 0.002

1.7

02/16/09 7,625,997.2 276.4 1,840.0 410.3 40 60.00 1.740 0.011

1.6

02/15/09 9,159,676.0 276.8 1,840.0 537.7 50 60.00 1.807 0.016

1.5

02/15/09 8,934,392.9 274.7 1,840.0 534.1 50 60.00 1.670 0.014

1.5

02/15/09 8,917,378.1 273.6 1,840.0 537.9 50 60.00 1.552 0.013

1.4

02/15/09 8,924,737.9 271.4 1,840.0 538.4 50 60.00 1.552 0.013

1.2

02/15/09 8,859,670.8 269.3 1,840.0 534.5 50 60.00 1.448 0.012

0.6

02/15/09 8,871,409.6 265.6 1,840.0 535.2 50 60.00 1.241 0.011

0.1

02/15/09 8,766,470.7 248.2 1,840.0 533.6 49 60.00 0.615 0.005

0.2

02/15/09 5,295,591.1 234.7 1,840.0 299.3 26 60.00 0.110 0.001

0.2

02/15/09 5,114,862.7 236.2 1,840.0 283.5 25 60.00 0.225 0.001

0.3

02/15/09 5,111,906.7 239.9 1,840.0 283.4 25 60.00 0.225 0.001

4.7

02/15/09 5,138,506.0 248.8 1,840.0 282.1 25 60.00 0.341 0.002

2.1

02/15/09 5,322,916.7 264.2 1,840.0 283.5 26 60.00 5.506 0.025

1.4

02/15/09 8,715,678.2 275.4 1,840.0 521.1 48 60.00 2.192 0.018

1.0

02/15/09 9,114,911.1 276.6 1,840.0 540.0 50 60.00 1.475 0.013

0.4

02/15/09 9,140,115.1 268.1 1,840.0 541.4 50 60.00 1.053 0.009

0.3

02/15/09 7,627,914.2 242.2 1,840.0 435.3 39 60.00 0.437 0.003

0.5

02/15/09 5,309,272.3 235.1 1,840.0 259.7 22 60.00 0.383 0.002

0.3

02/15/09 5,273,068.3 234.1 1,840.0 260.8 22 60.00 0.631 0.003

0.4

02/15/09 5,262,526.8 233.8 1,840.0 254.6 22 60.00 0.387 0.002

0.4

02/15/09 5,261,767.7 234.0 1,840.0 251.7 22 60.00 0.522 0.002

0.3

02/15/09 5,256,664.7 235.2 1,840.0 251.4 22 60.00 0.522 0.002

1.1

02/15/09 5,250,344.7 238.9 1,840.0 251.1 22 60.00 0.391 0.002

0.4

02/15/09 5,306,497.9 243.3 1,840.0 253.8 22 60.00 1.435 0.006

0.8

02/15/09 5,310,252.5 251.8 1,840.0 251.1 22 60.00 0.528 0.002

1.6

02/14/09 5,378,532.0 267.2 1,840.0 251.4 22 60.00 1.068 0.004

1.5

02/14/09 8,549,633.0 279.2 1,840.0 487.9 46 60.00 1.750 0.014

1.5

02/14/09 9,138,726.0 278.9 1,840.0 536.4 50 60.00 1.595 0.014

1.5

02/14/09 9,081,509.5 277.6 1,840.0 533.1 50 60.00 1.595 0.014

1.4

02/14/09 9,101,008.3 277.8 1,840.0 534.2 50 60.00 1.595 0.014

1.2

02/14/09 9,084,995.3 275.0 1,840.0 533.3 50 60.00 1.488 0.013

02/14/09 9,165,776.8 261.9 1,840.0 543.0 50 60.00 1.264 0.011
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 C

12:00 C

13:00

14:00

15:00

16:00

17:00

18:00 1.1

1.0

02/17/09 9,233,751.5 285.6 1,840.0 532.0 50 60.00 1.191 0.010

1.0

02/17/09 9,262,121.6 285.2 1,840.0 528.5 50 60.00 1.093 0.009

1.1

02/17/09 9,265,344.0 284.9 1,840.0 528.7 50 60.00 1.093 0.009

1.2

02/17/09 9,234,320.9 283.6 1,840.0 532.0 50 60.00 1.191 0.010

1.0

02/17/09 9,276,655.0 281.8 1,840.0 534.4 50 60.00 1.300 0.011

1.0

02/17/09 9,201,261.4 281.5 1,840.0 530.1 50 60.00 1.083 0.009

0.9

02/17/09 9,301,304.9 282.3 1,840.0 535.8 50 60.00 1.083 0.009

0.9

02/17/09 9,278,841.8 282.5 1,840.0 534.6 50 60.00 0.975 0.008

0.9

02/17/09 9,283,473.9 282.4 1,840.0 534.8 50 60.00 0.975 0.008

0.9

02/17/09 9,317,419.8 281.2 1,840.0 531.7 50 60.00 0.984 0.008

1.0

02/17/09 9,278,844.1 279.3 1,840.0 534.6 50 60.00 0.975 0.008

0.9

02/17/09 9,226,318.4 275.4 1,840.0 536.5 50 60.00 1.073 0.009

0.6

02/17/09 9,273,048.4 265.8 1,840.0 539.2 50 60.00 0.966 0.008

0.6

02/17/09 7,203,333.5 244.3 1,840.0 399.3 36 60.00 0.675 0.004

0.7

02/17/09 5,337,346.5 243.7 1,840.0 255.2 22 60.00 0.783 0.003

1.0

02/17/09 5,344,534.1 249.4 1,840.0 252.7 22 60.00 0.924 0.004

0.9

02/17/09 5,353,035.7 263.0 1,840.0 244.4 22 60.00 1.367 0.005

1.1

02/17/09 7,352,125.9 277.9 1,840.0 383.6 37 60.00 1.076 0.007

1.6

02/17/09 9,212,388.7 282.5 1,840.0 535.7 50 60.00 1.180 0.010

1.8

02/16/09 9,278,549.3 283.3 1,840.0 539.6 50 60.00 1.717 0.015

1.8

02/16/09 9,292,110.6 283.2 1,840.0 540.4 50 60.00 1.931 0.017

2.3

02/16/09 9,292,559.2 282.6 1,840.0 540.4 50 60.00 1.931 0.017

2.2

02/16/09 9,304,731.9 282.2 1,840.0 541.1 50 60.00 2.468 0.021

1.9

02/16/09 9,248,401.4 283.3 1,840.0 537.8 50 60.00 2.361 0.020

1.8

02/16/09 9,268,459.1 283.5 1,840.0 539.0 50 60.00 2.039 0.018

1.8

02/16/09 9,285,643.3 283.6 1,840.0 540.0 50 60.00 1.931 0.017

1.6

02/16/09 9,274,245.2 283.2 1,840.0 539.3 50 60.00 1.931 0.017

1.8

02/16/09 9,280,750.4 282.6 1,840.0 539.7 50 60.00 1.717 0.015

1.2

02/16/09 9,270,178.0 282.2 1,840.0 539.1 50 60.00 1.931 0.017

0.9

02/16/09 9,264,107.1 282.8 1,840.0 538.7 50 60.00 1.288 0.011

0.9

02/16/09 9,229,515.2 282.2 1,840.0 536.7 50 60.00 0.966 0.008

0.9

02/16/09 9,215,541.4 280.9 1,840.0 540.9 50 60.00 0.957 0.008

1.0

02/16/09 9,208,037.9 278.6 1,840.0 540.5 50 60.00 0.957 0.008

0.9

02/16/09 9,216,468.1 273.3 1,840.0 545.9 50 60.00 1.053 0.009

0.5

02/16/09 9,174,458.3 258.5 1,840.0 548.4 50 60.00 0.939 0.008

0.5

02/16/09 6,181,639.0 237.7 1,840.0 332.6 29 60.00 0.580 0.003

02/16/09 5,339,898.2 236.8 1,840.0 261.2 22 60.00 0.638 0.003
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00 0.9

0.6

02/19/09 9,079,143.8 260.0 1,840.0 532.9 50 60.00 0.957 0.008

0.8

02/19/09 8,411,697.6 235.1 1,840.0 498.3 45 60.00 0.632 0.005

0.7

02/19/09 5,109,377.5 222.8 1,840.0 252.7 23 60.00 1.009 0.004

0.6

02/19/09 5,043,289.0 223.7 1,840.0 243.9 22 60.00 0.903 0.004

0.6

02/19/09 5,035,473.2 225.2 1,840.0 240.8 22 60.00 0.783 0.003

0.7

02/19/09 5,012,416.3 229.4 1,840.0 234.3 22 60.00 0.801 0.003

0.7

02/19/09 4,967,533.0 238.6 1,840.0 237.6 22 60.00 0.913 0.003

0.9

02/19/09 5,023,968.1 255.4 1,840.0 234.8 22 60.00 0.935 0.004

1.3

02/18/09 8,306,054.1 269.2 1,840.0 478.5 47 60.00 0.975 0.007

1.1

02/18/09 9,076,363.6 270.4 1,840.0 547.5 53 60.00 1.345 0.012

1.3

02/18/09 9,009,754.4 273.3 1,840.0 543.5 52 60.00 1.138 0.010

1.3

02/18/09 9,160,328.7 279.6 1,840.0 552.6 53 60.00 1.345 0.012

1.3

02/18/09 9,340,298.8 280.2 1,840.0 553.3 53 60.00 1.369 0.012

1.2

02/18/09 9,362,916.3 279.9 1,840.0 554.7 53 60.00 1.369 0.012

1.1

02/18/09 9,307,446.3 280.2 1,840.0 546.3 53 60.00 1.276 0.011

1.1

02/18/09 9,314,073.0 281.1 1,840.0 546.7 53 60.00 1.169 0.010

1.2

02/18/09 9,340,265.0 280.7 1,840.0 548.2 53 60.00 1.169 0.010

1.1

02/18/09 9,288,851.1 279.8 1,840.0 545.2 53 60.00 1.276 0.011

1.0

02/18/09 9,311,858.2 281.8 1,840.0 546.6 53 60.00 1.169 0.010

0.9

02/18/09 9,311,823.0 282.5 1,840.0 546.6 53 60.00 1.063 0.009

1.0

02/18/09 9,361,435.9 280.7 1,840.0 549.5 53 60.00 0.957 0.008

0.8

02/18/09 9,330,047.1 274.6 1,840.0 547.6 53 60.00 1.063 0.009

1.2

02/18/09 9,317,295.8 255.9 1,840.0 551.9 52 60.00 0.843 0.007

1.0

02/18/09 5,536,700.0 235.4 1,840.0 279.9 26 60.00 1.481 0.007

0.8

02/18/09 5,125,970.3 236.6 1,840.0 245.2 22 60.00 1.305 0.005

0.7

02/18/09 5,164,587.6 237.6 1,840.0 244.2 22 60.00 1.056 0.004

0.6

02/18/09 5,188,263.0 237.6 1,840.0 245.3 22 60.00 0.924 0.004

0.7

02/18/09 5,192,427.4 238.2 1,840.0 242.7 22 60.00 0.801 0.003

0.6

02/18/09 5,180,085.7 240.3 1,840.0 244.9 22 60.00 0.924 0.004

0.5

02/18/09 5,192,246.7 243.5 1,840.0 239.8 22 60.00 0.810 0.003

0.8

02/18/09 5,207,137.0 248.9 1,840.0 249.0 22 60.00 0.652 0.003

1.0

02/18/09 5,225,850.7 262.3 1,840.0 244.3 22 60.00 1.068 0.004

1.2

02/17/09 6,837,560.3 279.3 1,840.0 341.9 33 60.00 1.248 0.007

1.1

02/17/09 9,219,020.3 283.1 1,840.0 526.1 50 60.00 1.312 0.011

1.1

02/17/09 9,223,187.1 282.5 1,840.0 526.3 50 60.00 1.203 0.010

1.0

02/17/09 9,209,154.8 283.1 1,840.0 530.5 50 60.00 1.191 0.010

02/17/09 9,201,749.4 284.8 1,840.0 530.1 50 60.00 1.083 0.009
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C S S SC

03:00 C

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00 0.5

0.6

02/20/09 9,135,878.8 278.8 1,840.0 526.3 50 60.00 0.542 0.005

0.5

02/20/09 9,112,007.1 279.9 1,840.0 529.9 50 60.00 0.644 0.005

0.6

02/20/09 9,169,702.6 279.8 1,840.0 533.3 50 60.00 0.537 0.005

0.6

02/20/09 9,102,133.8 278.9 1,840.0 529.3 50 60.00 0.644 0.005

0.6

02/20/09 9,127,560.5 279.1 1,840.0 530.8 50 60.00 0.644 0.005

0.6

02/20/09 9,157,407.2 278.9 1,840.0 527.5 50 60.00 0.650 0.005

1.0

02/20/09 9,142,324.6 278.0 1,840.0 526.7 50 60.00 0.650 0.005

1.0

02/20/09 9,140,602.5 277.5 1,840.0 531.6 50 60.00 1.073 0.009

1.1

02/20/09 9,162,803.4 277.7 1,840.0 532.8 50 60.00 1.073 0.009

1.0

02/20/09 9,174,632.1 276.9 1,840.0 528.6 50 60.00 1.191 0.010

0.9

02/20/09 9,173,019.4 275.3 1,840.0 528.4 50 60.00 1.083 0.009

0.8

02/20/09 9,121,548.8 274.5 1,840.0 520.5 50 60.00 0.984 0.008

0.8

02/20/09 9,164,403.9 274.1 1,840.0 527.9 50 60.00 0.867 0.007

0.9

02/20/09 9,111,569.8 272.8 1,840.0 529.9 50 60.00 0.858 0.007

0.9

02/20/09 9,136,180.2 272.2 1,840.0 526.3 50 60.00 0.975 0.008

0.8

02/20/09 9,097,437.0 273.9 1,840.0 529.0 50 60.00 0.966 0.008

0.9

02/20/09 9,151,634.9 274.6 1,840.0 527.2 50 60.00 0.867 0.007

0.9

02/20/09 9,119,197.6 273.9 1,840.0 525.3 50 60.00 0.975 0.008

0.9

02/20/09 9,072,345.0 272.8 1,840.0 522.6 50 60.00 0.975 0.008

0.9

02/20/09 9,121,863.7 271.7 1,840.0 530.5 50 60.00 0.966 0.008

1.4

02/20/09 9,130,876.3 271.8 1,840.0 531.0 50 60.00 0.966 0.008

1.7

02/19/09 9,154,644.9 274.1 1,840.0 532.4 50 60.00 1.502 0.013

1.7

02/19/09 9,205,336.8 274.9 1,840.0 535.3 50 60.00 1.824 0.016

2.0

02/19/09 9,209,124.1 274.8 1,840.0 530.5 50 60.00 1.841 0.016

1.8

02/19/09 9,212,067.7 275.0 1,840.0 530.7 50 60.00 2.166 0.018

1.7

02/19/09 9,207,319.0 276.2 1,840.0 530.4 50 60.00 1.950 0.017

1.6

02/19/09 9,221,513.6 276.9 1,840.0 531.3 50 60.00 1.841 0.016

2.1

02/19/09 9,223,956.7 276.2 1,840.0 531.4 50 60.00 1.733 0.015

1.8

02/19/09 9,193,889.6 274.7 1,840.0 529.7 50 60.00 2.275 0.019

1.8

02/19/09 9,201,777.0 273.9 1,840.0 530.1 50 60.00 1.950 0.017

1.4

02/19/09 9,185,438.3 274.6 1,840.0 534.1 50 60.00 1.931 0.016

1.0

02/19/09 9,193,308.8 274.9 1,840.0 534.6 50 60.00 1.502 0.013

1.0

02/19/09 9,195,796.7 273.6 1,840.0 529.8 50 60.00 1.083 0.009

0.9

02/19/09 9,123,099.8 272.1 1,840.0 530.5 50 60.00 1.073 0.009

0.8

02/19/09 9,105,907.0 272.4 1,840.0 529.5 50 60.00 0.966 0.008

0.8

02/19/09 9,126,820.7 271.9 1,840.0 530.8 50 60.00 0.858 0.007

02/19/09 9,125,890.4 268.8 1,840.0 530.7 50 60.00 0.858 0.007
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 FIT F F FIT F F FIT FIT FC

05:00 FIT F F FIT F F FIT FIT FC

06:00 FIT F F FIT F F FIT FIT F

07:00 FIT F F FIT F F FIT FIT F

08:00 FIT F F FIT F F FIT FIT F

09:00 FIT F F FIT F F FIT FIT 0.0 F

0.0

02/22/09 4,133,849.8 177.1 1,840.0 0 0.00

0.0

02/22/09 4,130,240.0 187.9 1,840.0 0 0.00

0.0

02/22/09 4,110,870.5 194.3 1,840.0 0 0.00

0.3

02/22/09 4,100,952.5 200.1 1,840.0 0 0.00

1.9

02/22/09 3,978,267.0 211.8 1,840.0 0 0.00

0.0

02/22/09 3,901,090.5 222.1 1,840.0 0 0.00

0.0

02/22/09 3,889,827.0 232.2 1,840.0 0.0 0 0.00 0.000

0.1

02/22/09 3,879,669.3 243.2 1,840.0 0.0 0 0.00 0.000

0.4

02/22/09 3,767,928.9 254.7 1,840.0 0.0 0 0.00 0.000

0.7

02/22/09 3,263,564.7 261.3 1,840.0 0.0 0 0.00 0.000

0.8

02/21/09 2,799,784.7 254.6 1,840.0 0.0 0 0.00 0.000

0.4

02/21/09 2,757,759.3 239.8 1,840.0 0.0 0 0.00 0.000

0.5

02/21/09 3,164,235.7 237.7 1,840.0 1.7 0 1.00 45.926 0.000

0.4

02/21/09 4,820,801.3 260.6 1,840.0 159.8 15 60.00 0.941 0.002

0.5

02/21/09 8,094,483.2 280.9 1,840.0 413.5 41 60.00 0.489 0.003

0.6

02/21/09 9,285,616.9 284.7 1,840.0 529.9 50 60.00 0.547 0.005

1.1

02/21/09 9,329,473.4 284.6 1,840.0 527.3 50 60.00 0.662 0.006

0.8

02/21/09 9,262,753.4 282.7 1,840.0 528.6 50 60.00 1.203 0.010

0.8

02/21/09 9,269,146.7 280.1 1,840.0 528.9 50 60.00 0.875 0.007

0.8

02/21/09 9,251,692.5 279.9 1,840.0 533.0 50 60.00 0.867 0.007

0.8

02/21/09 9,242,115.1 280.0 1,840.0 532.4 50 60.00 0.867 0.007

1.0

02/21/09 9,262,267.8 278.9 1,840.0 528.5 50 60.00 0.875 0.007

0.7

02/21/09 9,236,724.1 277.1 1,840.0 532.1 50 60.00 1.083 0.009

0.5

02/21/09 9,242,587.4 276.9 1,840.0 532.5 50 60.00 0.758 0.006

0.6

02/21/09 9,244,027.8 275.9 1,840.0 532.5 50 60.00 0.542 0.005

0.9

02/21/09 9,279,271.6 271.4 1,840.0 534.6 50 60.00 0.650 0.006

0.9

02/21/09 9,280,727.3 254.6 1,840.0 534.7 50 60.00 0.975 0.008

1.0

02/21/09 6,292,380.2 231.0 1,840.0 352.2 33 60.00 1.003 0.006

0.6

02/21/09 5,092,528.7 233.7 1,840.0 249.1 23 60.00 1.276 0.005

0.7

02/21/09 5,218,807.8 238.2 1,840.0 252.4 23 60.00 0.774 0.003

0.6

02/21/09 5,208,806.2 239.4 1,840.0 252.0 23 60.00 0.903 0.004

0.8

02/21/09 5,217,145.1 243.1 1,840.0 255.2 23 60.00 0.765 0.003

0.8

02/21/09 5,198,169.6 251.0 1,840.0 251.4 23 60.00 1.032 0.004

0.5

02/21/09 5,278,041.3 267.4 1,840.0 249.6 23 60.00 1.056 0.004

0.6

02/20/09 8,784,923.5 279.2 1,840.0 501.3 47 60.00 0.547 0.004

0.4

02/20/09 9,193,811.1 279.6 1,840.0 529.7 50 60.00 0.650 0.006

02/20/09 9,149,322.2 279.0 1,840.0 527.1 50 60.00 0.433 0.004
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

10:00 FIT F F FIT F F FIT FIT F

11:00 FIT F F FIT F F FIT FIT F

12:00 FIT F F FIT F F FIT FIT F

13:00 FIT F F FIT F F FIT FIT F

14:00 FIT F F FIT F F F FIT F

15:00 FIT F F FIT F F F FIT F

16:00 FIT F F FIT F F F FIT F

17:00 FIT F F FIT F F F FIT F

18:00 FIT F F FIT F F F FIT F

19:00 FIT F F FIT F F F FIT F

20:00 FIT F F FIT F F F FIT F

21:00 FIT F F FIT F F F FIT F

22:00 FIT F F FIT F F F FIT F

23:00 FIT F F FIT F F F FIT F

00:00 FIT F F FIT F F F FIT F

01:00 FIT F F FIT F F F FIT F

02:00 FIT F F FIT F F F FIT F

03:00 FIT F F FIT F F F FIT F

04:00 FIT F F FIT F F F FIT FC

05:00 FIT F F FIT F F F FIT FC

06:00 FIT F F FIT F F F FIT F

07:00 FIT F F FIT F F F FIT F

08:00 FIT F F FIT F F F FIT F

09:00 FIT F F FIT F F F FIT F

10:00 F F F F F F F F FC

11:00 F F F F F F F F FC

12:00 F F F F F F F F FC

13:00 F F F F F F F F FC

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F 0.0 F

0.0

02/23/09 1,132,067.5 65.9 1,840.0 0.0 0 0.00 0.000

0.0

02/23/09 1,133,003.6 66.5 1,840.0 0.0 0 0.00 0.000

0.0

02/23/09 1,110,166.5 67.1 1,840.0 0.0 0 0.00 0.000

0.0

02/23/09 1,101,054.8 67.7 1,840.0 0.0 0 0.00 0.000

0.0

02/23/09 1,051,932.9 68.7 1,840.0 0.0 0 0.00 0.000

0.0

02/23/09 1,081,859.3 70.2 1,840.0 0.0 0 0.00 0.000

0.0

02/23/09 1,085,720.8 71.7 1,840.0 0.0 0 0.00 0.000

0.0

02/23/09 1,242,787.1 75.3 1,840.0 0.0 0 0.00 0.000

0.5

02/23/09 1,361,459.2 76.9 1,840.0 0.0 0 0.00 0.000

2.2

02/23/09 1,363,026.4 77.3 1,840.0 0.0 0 0.00 0.000

0.9

02/23/09 1,413,941.1 77.7 1,840.0 0.0 0 0.00 0.000

1.6

02/23/09 1,414,463.3 77.7 1,840.0 0.0 0 0.00 0.000

0.0

02/23/09 1,474,906.2 77.8 1,840.0 0.0 0 0.00 0.000

0.0

02/23/09 1,492,155.0 77.9 1,840.0 0 0.00

0.0

02/23/09 1,595,864.0 78.3 1,840.0 0 0.00

0.0

02/23/09 1,641,792.9 78.9 1,840.0 0 0.00

0.2

02/23/09 1,633,046.9 79.9 1,840.0 0 0.00

2.4

02/23/09 1,654,688.9 81.1 1,840.0 0 0.00

0.0

02/23/09 1,687,157.4 82.5 1,840.0 0 0.00

0.0

02/23/09 1,679,592.3 84.0 1,840.0 0 0.00

0.0

02/23/09 3,140,259.0 85.8 1,840.0 0 0.00

0.0

02/23/09 1,673,245.1 87.5 1,840.0 0 0.00

0.0

02/23/09 1,666,823.5 89.4 1,840.0 0 0.00

0.0

02/22/09 2,078,714.8 91.9 1,840.0 0 0.00

0.0

02/22/09 3,222,655.8 95.0 1,840.0 0 0.00

0.0

02/22/09 3,241,444.5 97.8 1,840.0 0 0.00

0.0

02/22/09 3,081,394.3 100.7 1,840.0 0 0.00

0.0

02/22/09 3,062,085.3 102.9 1,840.0 0 0.00

0.0

02/22/09 2,980,534.3 104.8 1,840.0 0 0.00

0.0

02/22/09 3,095,614.5 108.2 1,840.0 0 0.00

0.0

02/22/09 3,143,915.8 112.0 1,840.0 0 0.00

0.0

02/22/09 3,121,852.5 116.4 1,840.0 0 0.00

0.0

02/22/09 3,136,348.5 121.5 1,840.0 0 0.00

0.0

02/22/09 3,281,453.5 128.9 1,840.0 0 0.00

0.0

02/22/09 4,256,907.5 141.6 1,840.0 0 0.00

0.0

02/22/09 4,025,861.0 151.7 1,840.0 0 0.00

02/22/09 4,139,916.3 164.2 1,840.0 0 0.00
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 ST ST ST ST ST

08:00 ST ST ST ST ST

09:00 ST ST ST ST STC

10:00 ST ST ST ST STC

11:00 ST ST ST ST C

12:00 STC ST ST ST C

13:00 C ST ST

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 0.3

0.5

02/25/09 8,962,614.7 278.3 1,840.0 526.1 50 60.00 0.319 0.003

0.6

02/25/09 8,960,817.0 276.6 1,840.0 530.8 50 60.00 0.527 0.004

0.5

02/25/09 8,935,951.0 276.1 1,840.0 529.4 50 60.00 0.632 0.005

0.4

02/25/09 8,985,980.3 276.0 1,840.0 527.4 50 60.00 0.532 0.004

0.3

02/25/09 8,983,743.5 272.8 1,840.0 532.2 50 60.00 0.421 0.004

0.2

02/25/09 9,026,018.6 261.4 1,840.0 534.7 50 60.00 0.316 0.003

0.2

02/25/09 6,958,600.3 244.8 1,840.0 397.1 36 60.00 0.219 0.001

0.1

02/25/09 5,596,979.1 245.5 1,840.0 292.0 26 60.00 0.239 0.001

0.0

02/25/09 5,665,284.3 248.1 1,840.0 292.5 26 60.00 0.121 0.001

0.3

02/25/09 5,667,152.2 256.2 1,840.0 295.7 26 60.00 0.000 0.000

0.3

02/25/09 6,867,804.2 268.8 1,840.0 358.3 34 60.00 0.359 0.002

0.3

02/25/09 9,064,378.9 275.8 1,840.0 522.2 50 60.00 0.325 0.003

0.6

02/24/09 9,306,045.5 277.3 1,840.0 526.0 50 60.00 0.331 0.003

0.9

02/24/09 8,837,994.3 277.6 1,840.0 538.0 50 60.00 0.615 0.005

1.0

02/24/09 9,220,846.6 275.3 1,840.0 541.2 50 60.00 0.957 0.008

0.9

02/24/09 9,318,376.3 271.2 1,840.0 541.9 50 60.00 1.073 0.009

0.8

02/24/09 9,328,861.8 265.7 1,840.0 542.5 50 60.00 0.966 0.008

0.8

02/24/09 9,536,628.3 244.1 1,840.0 549.4 50 60.00 0.867 0.008

1.7

02/24/09 5,831,162.9 207.7 1,840.0 313.7 28 60.00 0.928 0.005

2.3

02/24/09 5,069,641.9 200.2 1,840.0 234.2 20 60.00 2.296 0.009

1.8

02/24/09 5,052,544.8 190.5 1,840.0 230.7 20 60.00 3.144 0.012

1.6

02/24/09 4,699,317.6 178.2 1,840.0 163.4 10 60.00 3.229 0.008

0.6

02/24/09 4,491,817.4 169.8 1,840.0 80.6 4 60.00 5.567 0.007

1.3

02/24/09 3,164,000.0 161.4 1,840.0 56.7 0 60.00 2.088 0.002

0.8

02/24/09 3,164,000.0 145.2 1,840.0 56.7 0 60.00 4.523 0.004

0.8

02/24/09 3,164,000.0 130.7 1,840.0 56.7 0 60.00 2.783 0.003

0.8

02/24/09 3,164,000.0 116.0 1,840.0 56.7 0 60.00 2.783 0.003

0.8

02/24/09 3,164,000.0 99.1 1,840.0 56.7 0 60.00 2.783 0.003

0.0

02/24/09 3,164,000.0 88.1 1,840.0 56.7 0 29.00 2.783 0.001

0.2

02/24/09 1,102,450.8 64.9 1,840.0 0.0 0 0.00 0.000

2.4

02/24/09 1,126,223.5 64.8 1,840.0 0.0 0 0.00 0.000

0.0

02/24/09 1,126,914.3 65.0 1,840.0 0.0 0 0.00 0.000

0.0

02/24/09 1,135,149.6 65.2 1,840.0 0.0 0 0.00 0.000

0.0

02/24/09 2,791,843.5 65.3 1,840.0 0.0 0 0.00 0.000

0.0

02/24/09 1,134,512.4 65.3 1,840.0 0.0 0 0.00 0.000

0.0

02/24/09 1,136,241.2 65.4 1,840.0 0.0 0 0.00 0.000

02/23/09 1,132,090.6 65.4 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

12:00

13:00 S S SC

14:00 C

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 S S S

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00 0.4

0.3

02/27/09 5,633,406.1 252.8 1,840.0 284.7 26 60.00 0.494 0.002

0.3

02/26/09 5,815,575.9 265.7 1,840.0 287.6 26 60.00 0.379 0.002

0.4

02/26/09 8,697,033.7 277.1 1,840.0 496.3 48 60.00 0.328 0.003

0.6

02/26/09 8,867,647.6 278.9 1,840.0 515.7 50 60.00 0.429 0.004

0.5

02/26/09 8,836,250.3 278.9 1,840.0 518.6 50 60.00 0.638 0.005

0.7

02/26/09 8,723,988.4 279.3 1,840.0 516.8 49 60.00 0.527 0.004

0.7

02/26/09 8,988,438.1 281.5 1,840.0 532.4 50 60.00 0.737 0.006

0.6

02/26/09 9,095,904.8 281.4 1,840.0 543.8 51 60.00 0.731 0.006

0.6

02/26/09 9,129,892.9 281.7 1,840.0 540.9 51 60.00 0.632 0.005

0.6

02/26/09 9,224,141.8 281.1 1,840.0 546.4 52 60.00 0.632 0.006

0.6

02/26/09 9,238,970.1 281.1 1,840.0 542.3 52 60.00 0.638 0.006

0.7

02/26/09 9,301,789.9 281.5 1,840.0 546.0 52 60.00 0.638 0.006

0.7

02/26/09 9,262,252.1 281.2 1,840.0 543.6 52 60.00 0.744 0.006

0.8

02/26/09 9,315,430.6 281.2 1,840.0 541.7 52 60.00 0.751 0.007

0.8

02/26/09 9,224,852.9 278.7 1,840.0 546.5 51 60.00 0.843 0.007

0.7

02/26/09 9,085,897.4 277.6 1,840.0 533.3 50 60.00 0.850 0.007

0.5

02/26/09 9,060,825.2 279.2 1,840.0 536.8 50 60.00 0.737 0.006

0.5

02/26/09 9,047,850.7 278.7 1,840.0 531.1 50 60.00 0.532 0.005

0.6

02/26/09 8,991,465.0 274.7 1,840.0 532.6 50 60.00 0.527 0.004

0.2

02/26/09 9,033,432.8 262.0 1,840.0 530.2 50 60.00 0.638 0.005

0.1

02/26/09 6,598,770.8 246.9 1,840.0 369.4 34 60.00 0.223 0.001

0.1

02/26/09 5,709,388.9 247.1 1,840.0 291.7 26 60.00 0.122 0.001

0.4

02/26/09 5,729,062.1 249.1 1,840.0 289.6 26 60.00 0.123 0.001

0.7

02/26/09 5,543,257.3 253.9 1,840.0 289.2 26 60.00 0.478 0.002

0.6

02/26/09 5,628,613.1 265.7 1,840.0 290.6 26 60.00 0.846 0.004

0.5

02/25/09 7,810,140.5 278.8 1,840.0 445.7 42 60.00 0.656 0.005

0.5

02/25/09 8,900,342.8 282.0 1,840.0 527.2 50 60.00 0.527 0.004

0.6

02/25/09 8,953,844.5 283.2 1,840.0 530.4 50 60.00 0.527 0.004

0.7

02/25/09 8,961,642.8 283.2 1,840.0 530.9 50 60.00 0.632 0.005

0.8

02/25/09 8,965,367.6 281.8 1,840.0 531.1 50 60.00 0.737 0.006

0.7

02/25/09 8,981,793.0 280.5 1,840.0 532.1 50 60.00 0.843 0.007

0.6

02/25/09 8,986,468.9 280.3 1,840.0 532.3 50 60.00 0.737 0.006

0.6

02/25/09 8,979,691.1 280.9 1,840.0 532.0 50 60.00 0.632 0.005

0.6

02/25/09 9,017,015.8 280.2 1,840.0 529.3 50 60.00 0.638 0.005

0.5

02/25/09 8,997,852.1 278.5 1,840.0 528.1 50 60.00 0.638 0.005

0.4

02/25/09 8,973,602.1 278.0 1,840.0 526.7 50 60.00 0.532 0.004

02/25/09 8,973,440.3 278.4 1,840.0 526.7 50 60.00 0.425 0.004
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

01:00 C

02:00 C S S SC

03:00 C

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 S S S

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00 0.6

0.7

02/28/09 9,372,034.3 289.0 1,840.0 555.2 51 60.00 0.632 0.006

0.8

02/28/09 9,404,858.2 287.1 1,840.0 557.1 51 60.00 0.737 0.007

0.8

02/28/09 9,369,939.1 284.0 1,840.0 555.1 51 60.00 0.843 0.007

0.7

02/28/09 9,376,384.0 280.5 1,840.0 555.4 51 60.00 0.843 0.007

0.7

02/28/09 9,454,509.9 274.0 1,840.0 560.1 51 60.00 0.737 0.007

1.2

02/28/09 8,887,111.2 248.6 1,840.0 526.5 48 60.00 0.737 0.006

1.0

02/28/09 5,435,008.3 228.0 1,840.0 245.2 21 60.00 1.660 0.007

1.2

02/28/09 5,270,436.8 228.3 1,840.0 229.1 20 60.00 1.435 0.005

1.0

02/28/09 5,189,192.8 230.4 1,840.0 225.6 20 60.00 1.722 0.006

0.9

02/28/09 5,312,099.2 235.3 1,840.0 233.8 20 60.00 1.417 0.005

0.8

02/28/09 5,304,313.2 243.8 1,840.0 230.6 20 60.00 1.292 0.005

0.7

02/28/09 5,403,114.8 261.1 1,840.0 229.0 20 60.00 1.178 0.004

0.6

02/28/09 8,208,011.4 273.7 1,840.0 463.9 43 60.00 0.773 0.006

0.6

02/28/09 9,029,502.9 276.3 1,840.0 530.0 48 60.00 0.638 0.005

0.6

02/27/09 9,030,002.8 278.4 1,840.0 530.0 48 60.00 0.638 0.005

0.7

02/27/09 9,053,991.3 278.1 1,840.0 531.4 48 60.00 0.638 0.005

0.6

02/27/09 9,087,867.9 277.6 1,840.0 528.5 48 60.00 0.751 0.006

0.6

02/27/09 9,088,884.4 278.1 1,840.0 533.5 48 60.00 0.638 0.005

0.7

02/27/09 9,021,156.1 277.3 1,840.0 529.5 48 60.00 0.638 0.005

0.7

02/27/09 9,062,679.6 276.1 1,840.0 532.0 48 60.00 0.744 0.006

0.7

02/27/09 8,957,276.5 275.2 1,840.0 525.7 48 60.00 0.744 0.006

0.6

02/27/09 8,978,855.6 277.2 1,840.0 527.0 48 60.00 0.744 0.006

0.6

02/27/09 8,927,019.6 279.3 1,840.0 524.0 48 60.00 0.638 0.005

0.7

02/27/09 9,043,909.2 280.4 1,840.0 525.9 48 60.00 0.644 0.005

0.7

02/27/09 9,131,064.7 281.0 1,840.0 540.9 50 60.00 0.737 0.006

0.7

02/27/09 9,208,199.5 280.0 1,840.0 540.5 50 60.00 0.744 0.006

0.7

02/27/09 9,230,923.7 279.8 1,840.0 541.8 50 60.00 0.744 0.006

0.7

02/27/09 9,198,316.1 278.7 1,840.0 539.9 50 60.00 0.744 0.006

0.6

02/27/09 9,187,882.3 278.4 1,840.0 539.3 50 60.00 0.744 0.006

0.6

02/27/09 9,151,746.4 279.0 1,840.0 542.2 50 60.00 0.632 0.005

0.5

02/27/09 9,195,221.0 278.7 1,840.0 539.7 50 60.00 0.638 0.006

0.5

02/27/09 9,210,558.3 274.9 1,840.0 540.6 50 60.00 0.532 0.005

0.3

02/27/09 9,292,148.8 265.5 1,840.0 540.4 50 60.00 0.537 0.005

0.3

02/27/09 7,664,240.0 246.4 1,840.0 441.5 41 60.00 0.325 0.002

0.3

02/27/09 5,706,645.1 243.6 1,840.0 285.3 26 60.00 0.374 0.002

0.4

02/27/09 5,856,018.5 243.8 1,840.0 286.4 26 60.00 0.383 0.002

02/27/09 5,672,477.3 245.6 1,840.0 289.8 26 60.00 0.489 0.002
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 S S S

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00 C

18:00 C

19:00

20:00

21:00

22:00

23:00

00:00

01:00 S S S

02:00 C 1.5

1.3

03/02/09 5,502,558.8 263.7 1,840.0 257.2 22 60.00 2.003 0.008

1.1

03/02/09 8,646,650.8 276.3 1,840.0 498.1 46 60.00 1.408 0.011

1.2

03/02/09 9,305,907.9 278.6 1,840.0 546.2 50 60.00 1.169 0.010

1.4

03/01/09 9,250,230.3 279.6 1,840.0 548.0 50 60.00 1.264 0.011

1.7

03/01/09 9,256,905.7 281.0 1,840.0 548.4 50 60.00 1.475 0.013

1.6

03/01/09 9,248,858.9 281.9 1,840.0 547.9 50 60.00 1.791 0.016

2.0

03/01/09 9,285,892.4 281.6 1,840.0 550.1 50 60.00 1.685 0.015

1.5

03/01/09 9,276,590.1 280.0 1,840.0 549.6 50 60.00 2.107 0.019

1.1

03/01/09 9,251,322.3 279.8 1,840.0 548.0 50 60.00 1.580 0.014

1.2

03/01/09 9,279,968.5 280.9 1,840.0 549.7 50 60.00 1.159 0.010

1.1

03/01/09 9,286,721.3 280.5 1,840.0 545.1 50 60.00 1.276 0.011

1.2

03/01/09 9,280,632.0 280.7 1,840.0 544.8 50 60.00 1.169 0.010

1.0

03/01/09 9,273,047.0 281.6 1,840.0 544.3 50 60.00 1.276 0.011

0.7

03/01/09 9,270,810.8 282.5 1,840.0 549.2 50 60.00 1.053 0.009

0.8

03/01/09 9,317,018.8 283.0 1,840.0 546.9 50 60.00 0.744 0.007

0.8

03/01/09 9,291,849.1 281.6 1,840.0 550.5 50 60.00 0.843 0.007

0.7

03/01/09 9,283,127.9 279.6 1,840.0 549.9 50 60.00 0.843 0.007

0.7

03/01/09 9,223,628.8 279.6 1,840.0 546.4 50 60.00 0.737 0.006

0.7

03/01/09 9,275,212.6 277.0 1,840.0 544.4 50 60.00 0.744 0.006

1.3

03/01/09 9,257,696.9 265.7 1,840.0 548.4 50 60.00 0.737 0.006

1.4

03/01/09 7,525,703.7 238.6 1,840.0 417.2 38 60.00 1.463 0.010

1.1

03/01/09 5,332,697.7 237.3 1,840.0 246.4 22 60.00 1.891 0.007

1.0

03/01/09 5,419,163.8 245.3 1,840.0 247.4 22 60.00 1.504 0.006

1.1

03/01/09 5,822,890.0 254.7 1,840.0 272.2 25 60.00 1.335 0.006

0.9

03/01/09 7,474,854.6 243.7 1,840.0 385.9 40 60.00 1.329 0.008

0.8

03/01/09 5,373,586.0 239.4 1,840.0 251.2 22 60.00 1.202 0.005

0.8

03/01/09 5,410,365.3 242.6 1,840.0 247.0 22 60.00 1.093 0.004

0.7

02/28/09 5,412,178.2 248.7 1,840.0 250.0 22 60.00 1.081 0.004

0.6

02/28/09 5,454,183.7 259.6 1,840.0 249.0 22 60.00 0.957 0.004

0.7

02/28/09 5,937,677.9 279.1 1,840.0 271.1 25 60.00 0.820 0.004

0.7

02/28/09 9,267,280.3 289.0 1,840.0 549.0 51 60.00 0.737 0.006

0.7

02/28/09 9,365,847.6 288.4 1,840.0 554.8 51 60.00 0.737 0.007

0.6

02/28/09 9,340,717.5 288.1 1,840.0 553.4 52 60.00 0.737 0.007

0.6

02/28/09 9,347,136.0 287.1 1,840.0 553.7 51 60.00 0.632 0.006

0.6

02/28/09 9,366,198.5 287.2 1,840.0 554.8 51 60.00 0.632 0.006

0.6

02/28/09 9,317,404.0 288.2 1,840.0 557.0 51 60.00 0.626 0.006

02/28/09 9,383,972.2 288.9 1,840.0 555.9 51 60.00 0.632 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00 C

10:00 S S SC

11:00 C

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 C

12:00 C

13:00

14:00

15:00 1.4

1.6

03/03/09 9,221,808.8 278.5 1,840.0 546.3 50 60.00 1.475 0.013

1.1

03/03/09 9,205,770.2 278.5 1,840.0 545.4 50 60.00 1.685 0.015

1.1

03/03/09 9,240,213.3 279.4 1,840.0 547.4 50 60.00 1.159 0.010

1.2

03/03/09 9,211,509.1 279.2 1,840.0 545.7 50 60.00 1.159 0.010

1.1

03/03/09 9,210,669.9 278.0 1,840.0 550.7 50 60.00 1.253 0.011

1.0

03/03/09 9,178,434.1 276.9 1,840.0 548.7 50 60.00 1.148 0.010

1.0

03/03/09 9,178,259.6 276.0 1,840.0 548.7 50 60.00 1.044 0.009

0.9

03/03/09 9,154,625.4 274.0 1,840.0 547.3 50 60.00 1.044 0.009

1.0

03/03/09 9,150,972.6 269.9 1,840.0 542.1 50 60.00 0.948 0.008

1.5

03/03/09 9,197,320.1 255.0 1,840.0 549.8 50 60.00 1.044 0.009

1.0

03/03/09 6,841,610.6 226.9 1,840.0 349.5 32 60.00 1.832 0.010

0.8

03/03/09 5,481,815.3 226.1 1,840.0 238.3 22 60.00 1.435 0.005

0.7

03/03/09 5,538,935.3 231.2 1,840.0 225.8 22 60.00 1.225 0.004

0.8

03/03/09 5,467,754.6 241.6 1,840.0 225.9 22 60.00 1.058 0.004

0.8

03/03/09 5,479,383.0 258.4 1,840.0 226.3 22 60.00 1.209 0.004

0.8

03/03/09 7,984,096.5 276.1 1,840.0 429.6 41 60.00 0.928 0.006

1.0

03/02/09 9,173,247.7 279.3 1,840.0 543.4 50 60.00 0.843 0.007

1.0

03/02/09 9,216,063.1 279.9 1,840.0 540.9 50 60.00 1.063 0.009

1.0

03/02/09 9,313,977.8 280.1 1,840.0 546.7 50 60.00 1.063 0.009

1.2

03/02/09 9,215,301.1 279.5 1,840.0 540.9 50 60.00 1.063 0.009

1.2

03/02/09 9,154,500.2 278.1 1,840.0 542.3 50 60.00 1.264 0.011

1.1

03/02/09 9,143,600.1 276.8 1,840.0 541.7 50 60.00 1.264 0.011

0.9

03/02/09 9,144,983.5 277.6 1,840.0 546.7 50 60.00 1.148 0.010

1.0

03/02/09 9,266,691.3 278.2 1,840.0 549.0 50 60.00 0.948 0.008

1.1

03/02/09 9,253,023.9 278.5 1,840.0 548.1 50 60.00 1.053 0.009

0.8

03/02/09 9,272,551.4 278.4 1,840.0 544.3 50 60.00 1.169 0.010

0.9

03/02/09 9,250,779.4 278.0 1,840.0 543.0 50 60.00 0.850 0.007

1.1

03/02/09 9,265,959.5 276.9 1,840.0 543.9 50 60.00 0.957 0.008

1.3

03/02/09 9,245,029.3 275.4 1,840.0 537.6 50 60.00 1.180 0.010

1.5

03/02/09 9,205,942.0 274.0 1,840.0 540.4 50 60.00 1.382 0.012

1.4

03/02/09 9,243,936.3 272.0 1,840.0 542.6 50 60.00 1.595 0.014

0.9

03/02/09 9,222,126.9 270.6 1,840.0 541.3 50 60.00 1.488 0.013

1.1

03/02/09 9,211,088.7 262.5 1,840.0 545.7 50 60.00 0.948 0.008

1.5

03/02/09 8,060,354.3 239.4 1,840.0 473.1 43 60.00 1.169 0.009

1.4

03/02/09 5,369,704.8 233.9 1,840.0 251.0 22 60.00 2.003 0.008

1.3

03/02/09 5,417,035.2 238.2 1,840.0 250.2 22 60.00 1.891 0.008

03/02/09 5,394,866.8 246.8 1,840.0 246.3 22 60.00 1.777 0.007
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 S S S

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00 * *

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 2.0 C

1.8

03/05/09 5,224,359.7 230.9 1,840.0 244.2 22 60.00 2.670 0.010

1.4

03/05/09 5,465,420.6 231.9 1,840.0 252.5 23 60.00 2.431 0.010

1.4

03/05/09 5,261,985.2 233.8 1,840.0 245.9 22 60.00 1.869 0.007

1.4

03/05/09 5,308,701.3 235.5 1,840.0 248.1 22 60.00 1.869 0.007

1.3

03/05/09 5,312,279.8 238.8 1,840.0 245.4 22 60.00 1.891 0.007

1.4

03/04/09 5,354,681.0 247.2 1,840.0 244.5 22 60.00 1.777 0.007

1.0

03/04/09 5,525,419.6 264.0 1,840.0 243.2 22 60.00 1.984 0.008

1.0

03/04/09 8,411,930.7 278.9 1,840.0 466.3 44 60.00 1.126 0.008

1.1

03/04/09 9,126,200.8 280.0 1,840.0 535.7 50 60.00 1.063 0.009

1.1

03/04/09 9,182,883.7 278.7 1,840.0 539.0 50 60.00 1.169 0.010

1.0

03/04/09 9,158,507.3 278.1 1,840.0 537.6 50 60.00 1.169 0.010

0.9

03/04/09 9,103,482.5 278.7 1,840.0 534.3 50 60.00 1.063 0.009

0.9

03/04/09 9,208,223.6 278.5 1,840.0 535.5 50 60.00 0.966 0.008

0.9

03/04/09 9,201,853.9 277.8 1,840.0 535.1 50 60.00 0.966 0.008

0.9

03/04/09 9,183,678.5 277.2 1,840.0 534.1 50 60.00 0.966 0.008

0.8

03/04/09 9,180,443.1 277.3 1,840.0 533.8 50 60.00 0.966 0.008

0.9

03/04/09 9,180,320.8 277.9 1,840.0 528.8 50 60.00 0.867 0.007

1.0

03/04/09 9,153,423.9 277.6 1,840.0 532.3 50 60.00 0.966 0.008

0.9

03/04/09 9,204,323.6 275.3 1,840.0 540.2 50 60.00 1.063 0.009

1.0

03/04/09 9,106,385.0 273.9 1,840.0 539.4 50 60.00 0.948 0.008

0.8

03/04/09 9,142,546.7 270.8 1,840.0 541.6 50 60.00 1.053 0.009

1.3

03/04/09 9,031,143.8 254.5 1,840.0 539.9 50 60.00 0.835 0.007

2.0

03/04/09 6,411,701.9 232.0 1,840.0 348.5 32 60.00 1.493 0.008

1.4

03/04/09 5,259,251.0 231.0 1,840.0 254.4 23 60.00 2.580 0.010

1.4

03/04/09 5,335,670.0 232.7 1,840.0 255.2 23 60.00 1.827 0.007

1.2

03/04/09 5,328,057.8 233.7 1,840.0 254.8 23 60.00 1.827 0.007

1.4

03/04/09 5,393,097.1 235.8 1,840.0 257.9 23 60.00 1.566 0.006

1.6

03/04/09 5,365,951.9 238.7 1,840.0 256.6 23 60.00 1.827 0.007

1.6

03/04/09 5,380,532.4 245.9 1,840.0 257.4 23 60.00 2.088 0.009

1.4

03/03/09 5,466,479.6 259.5 1,840.0 255.5 23 60.00 2.136 0.009

1.5

03/03/09 6,971,573.5 277.0 1,840.0 356.2 34 60.00 1.710 0.010

1.3

03/03/09 9,216,519.3 280.3 1,840.0 546.0 50 60.00 1.580 0.014

1.2

03/03/09 9,224,856.4 281.0 1,840.0 546.5 50 60.00 1.369 0.012

1.3

03/03/09 9,218,985.6 282.0 1,840.0 546.1 50 60.00 1.264 0.011

1.2

03/03/09 9,239,141.8 281.3 1,840.0 547.3 50 60.00 1.369 0.012

1.2

03/03/09 9,235,918.2 280.9 1,840.0 547.1 50 60.00 1.264 0.011

03/03/09 9,177,074.3 280.0 1,840.0 548.6 50 60.00 1.253 0.011
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C S S SC

03:00 C

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00 1.0

0.7

03/06/09 6,499,912.1 247.7 1,840.0 307.3 27 60.00 1.320 0.006

0.7

03/06/09 6,002,886.7 246.4 1,840.0 270.8 25 60.00 0.968 0.004

1.4

03/06/09 6,052,066.2 244.4 1,840.0 273.0 25 60.00 0.968 0.004

1.6

03/06/09 5,881,348.5 239.9 1,840.0 255.7 23 60.00 2.009 0.008

2.3

03/06/09 5,420,883.3 236.5 1,840.0 241.6 21 60.00 2.240 0.009

2.1

03/06/09 5,124,668.9 235.3 1,840.0 236.8 21 60.00 3.107 0.012

1.7

03/06/09 5,130,037.5 235.6 1,840.0 239.8 21 60.00 2.804 0.011

1.6

03/06/09 5,153,557.7 236.5 1,840.0 238.1 21 60.00 2.296 0.009

1.5

03/06/09 5,200,971.9 236.0 1,840.0 237.4 21 60.00 2.187 0.008

1.5

03/06/09 5,266,635.1 235.2 1,840.0 237.6 21 60.00 2.075 0.008

1.4

03/06/09 5,235,002.5 235.4 1,840.0 236.1 21 60.00 2.075 0.008

1.3

03/06/09 5,214,927.4 237.0 1,840.0 235.2 21 60.00 1.937 0.007

1.3

03/06/09 5,248,164.9 237.2 1,840.0 236.7 21 60.00 1.798 0.007

1.1

03/06/09 5,223,278.1 237.0 1,840.0 232.8 21 60.00 1.820 0.007

1.0

03/06/09 5,241,073.2 237.1 1,840.0 230.7 21 60.00 1.559 0.006

1.0

03/06/09 5,165,643.3 239.1 1,840.0 233.0 21 60.00 1.383 0.005

1.0

03/06/09 5,223,642.3 242.1 1,840.0 232.8 21 60.00 1.400 0.005

1.2

03/06/09 5,235,373.6 247.7 1,840.0 233.3 21 60.00 1.400 0.005

0.7

03/05/09 5,219,887.8 261.1 1,840.0 232.6 21 60.00 1.680 0.006

0.7

03/05/09 6,976,195.9 278.7 1,840.0 337.4 33 60.00 0.903 0.005

0.5

03/05/09 9,282,280.7 281.1 1,840.0 534.7 50 60.00 0.758 0.006

1.0

03/05/09 9,389,726.8 276.6 1,840.0 535.8 50 60.00 0.547 0.005

1.3

03/05/09 9,171,320.6 259.1 1,840.0 543.3 50 60.00 1.053 0.009

1.3

03/05/09 5,847,497.0 238.1 1,840.0 292.4 27 60.00 1.622 0.008

1.4

03/05/09 5,248,498.5 236.5 1,840.0 245.3 22 60.00 1.736 0.007

1.8

03/05/09 5,238,794.5 234.5 1,840.0 244.9 22 60.00 1.869 0.007

1.8

03/05/09 5,187,839.9 233.3 1,840.0 245.3 22 60.00 2.376 0.009

1.5

03/05/09 5,203,041.9 233.2 1,840.0 243.2 22 60.00 2.403 0.009

1.4

03/05/09 5,233,929.1 234.1 1,840.0 244.6 22 60.00 2.003 0.008

1.4

03/05/09 5,277,255.4 234.0 1,840.0 246.6 22 60.00 1.869 0.007

1.2

03/05/09 5,277,622.4 232.8 1,840.0 246.7 22 60.00 1.869 0.007

1.5

03/05/09 5,275,235.8 232.4 1,840.0 246.5 22 60.00 1.602 0.006

1.5

03/05/09 5,248,649.6 233.4 1,840.0 245.3 22 60.00 2.003 0.008

1.5

03/05/09 5,284,267.2 233.4 1,840.0 247.0 22 60.00 2.003 0.008

1.5

03/05/09 5,295,742.1 232.4 1,840.0 247.5 22 60.00 2.003 0.008

2.1

03/05/09 5,274,614.4 231.1 1,840.0 246.5 22 60.00 2.003 0.008

03/05/09 5,226,340.7 230.4 1,840.0 247.1 22 60.00 2.771 0.011
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 S S S

02:00 C

03:00

04:00 C

05:00 C C

06:00 0.3

0.3

03/08/09 4,998,718.9 229.2 1,840.0 252.7 22 60.00 0.370 0.001

0.4

03/08/09 5,064,470.0 229.9 1,840.0 256.0 22 60.00 0.370 0.002

0.4

03/08/09 5,137,445.8 230.3 1,840.0 259.6 22 60.00 0.494 0.002

0.3

03/08/09 5,027,446.2 232.4 1,840.0 251.3 22 60.00 0.499 0.002

0.2

03/08/09 5,088,476.4 236.3 1,840.0 254.4 22 60.00 0.374 0.002

0.2

03/08/09 5,125,060.0 240.8 1,840.0 256.3 22 60.00 0.250 0.001

0.5

03/08/09 5,421,072.9 247.7 1,840.0 276.9 24 60.00 0.244 0.001

0.4

03/07/09 5,631,149.5 257.5 1,840.0 296.9 26 60.00 0.592 0.003

0.2

03/07/09 7,108,340.2 271.4 1,840.0 370.9 35 60.00 0.478 0.003

0.2

03/07/09 9,317,117.5 275.6 1,840.0 536.7 50 60.00 0.217 0.002

0.2

03/07/09 9,398,968.6 272.3 1,840.0 536.4 50 60.00 0.219 0.002

0.1

03/07/09 9,209,015.4 255.9 1,840.0 545.5 50 60.00 0.211 0.002

0.2

03/07/09 6,423,827.6 232.3 1,840.0 356.1 32 60.00 0.113 0.001

0.2

03/07/09 4,969,944.0 231.0 1,840.0 240.4 22 60.00 0.258 0.001

0.7

03/07/09 5,025,307.1 232.9 1,840.0 240.3 23 60.00 0.261 0.001

0.6

03/07/09 4,983,967.8 232.1 1,840.0 241.1 21 60.00 0.903 0.003

0.8

03/07/09 4,961,237.8 231.5 1,840.0 237.3 21 60.00 0.783 0.003

0.8

03/07/09 4,947,694.3 231.2 1,840.0 236.6 21 60.00 1.044 0.004

0.5

03/07/09 4,958,435.0 231.4 1,840.0 250.6 22 60.00 0.988 0.004

0.5

03/07/09 4,961,907.2 231.7 1,840.0 248.1 22 60.00 0.624 0.002

0.4

03/07/09 5,000,490.5 231.5 1,840.0 250.0 22 60.00 0.624 0.002

0.3

03/07/09 5,044,136.5 231.8 1,840.0 252.2 22 60.00 0.499 0.002

0.3

03/07/09 5,017,673.6 232.8 1,840.0 248.2 22 60.00 0.379 0.002

0.1

03/07/09 4,945,129.4 236.5 1,840.0 247.3 22 60.00 0.374 0.001

0.0

03/07/09 5,203,027.0 241.2 1,840.0 260.2 23 60.00 0.125 0.001

0.1

03/07/09 5,702,222.9 242.6 1,840.0 297.5 26 60.00 0.000 0.000

0.2

03/07/09 5,385,515.9 243.6 1,840.0 281.0 26 60.00 0.120 0.001

0.1

03/07/09 6,095,780.6 246.8 1,840.0 281.6 26 60.00 0.270 0.001

0.1

03/07/09 6,153,176.6 248.5 1,840.0 284.2 26 60.00 0.135 0.001

0.3

03/07/09 6,155,198.7 250.9 1,840.0 284.3 26 60.00 0.135 0.001

1.0

03/07/09 6,156,239.2 257.7 1,840.0 284.4 26 60.00 0.405 0.002

0.6

03/06/09 6,601,943.5 271.5 1,840.0 305.0 28 60.00 1.351 0.007

0.4

03/06/09 9,276,609.4 278.4 1,840.0 544.5 50 60.00 0.638 0.006

0.3

03/06/09 9,357,407.7 277.2 1,840.0 549.2 50 60.00 0.425 0.004

0.5

03/06/09 9,373,965.3 265.7 1,840.0 550.2 50 60.00 0.319 0.003

1.0

03/06/09 6,743,965.3 249.9 1,840.0 340.9 31 60.00 0.617 0.003

03/06/09 6,176,420.2 248.6 1,840.0 285.3 26 60.00 1.351 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00 0.3

0.2

03/09/09 9,347,204.5 280.3 1,840.0 543.5 50 60.00 0.322 0.003

0.4

03/09/09 9,232,506.6 281.8 1,840.0 531.9 49 60.00 0.217 0.002

0.4

03/09/09 9,732,277.2 284.1 1,840.0 550.1 50 60.00 0.442 0.004

0.4

03/09/09 9,879,649.5 285.3 1,840.0 563.8 51 60.00 0.437 0.004

0.5

03/09/09 9,925,160.2 285.4 1,840.0 566.4 51 60.00 0.437 0.004

0.6

03/09/09 9,961,136.3 284.4 1,840.0 568.4 51 60.00 0.547 0.005

0.7

03/09/09 9,950,595.0 283.7 1,840.0 562.4 51 60.00 0.662 0.006

0.7

03/09/09 9,917,538.6 285.1 1,840.0 560.6 51 60.00 0.773 0.007

0.7

03/09/09 9,959,657.5 285.5 1,840.0 563.0 51 60.00 0.773 0.007

0.7

03/09/09 9,977,939.4 284.0 1,840.0 564.0 51 60.00 0.773 0.007

0.6

03/09/09 9,913,911.7 281.4 1,840.0 565.7 50 60.00 0.765 0.007

0.6

03/09/09 9,790,197.9 282.1 1,840.0 558.7 50 60.00 0.656 0.006

0.7

03/09/09 9,801,735.5 281.8 1,840.0 559.4 50 60.00 0.656 0.006

0.6

03/09/09 9,795,336.4 279.6 1,840.0 559.0 50 60.00 0.765 0.007

0.5

03/09/09 9,844,770.1 272.3 1,840.0 556.5 50 60.00 0.662 0.006

0.5

03/09/09 8,786,849.7 249.8 1,840.0 496.7 44 60.00 0.552 0.004

0.3

03/09/09 5,888,590.3 241.5 1,840.0 300.9 26 60.00 0.611 0.003

0.1

03/09/09 5,787,862.3 243.1 1,840.0 295.7 26 60.00 0.366 0.002

0.2

03/09/09 5,806,340.2 243.9 1,840.0 299.8 25 60.00 0.121 0.001

0.3

03/09/09 5,657,018.8 244.7 1,840.0 298.2 25 60.00 0.237 0.001

0.2

03/08/09 5,638,040.1 252.1 1,840.0 297.2 25 60.00 0.355 0.002

0.2

03/08/09 5,781,624.3 265.0 1,840.0 292.2 25 60.00 0.247 0.001

0.2

03/08/09 9,079,969.4 273.9 1,840.0 503.3 47 60.00 0.225 0.002

0.1

03/08/09 9,304,996.4 270.4 1,840.0 546.2 51 60.00 0.213 0.002

0.0

03/08/09 9,368,890.4 264.3 1,840.0 544.8 51 60.00 0.107 0.001

0.4

03/08/09 8,499,725.5 235.3 1,840.0 498.9 44 60.00 0.000 0.000

0.5

03/08/09 4,853,834.5 218.7 1,840.0 226.9 21 60.00 0.534 0.002

0.5

03/08/09 4,846,944.3 219.6 1,840.0 226.5 21 60.00 0.668 0.002

0.7

03/08/09 4,856,921.3 222.2 1,840.0 232.3 22 60.00 0.652 0.002

1.0

03/08/09 4,904,809.1 223.8 1,840.0 245.3 22 60.00 0.874 0.003

0.9

03/08/09 4,951,618.3 224.0 1,840.0 250.3 22 60.00 1.235 0.005

0.8

03/08/09 4,914,186.4 223.6 1,840.0 248.4 22 60.00 1.111 0.004

0.5

03/08/09 4,918,923.2 224.5 1,840.0 251.3 22 60.00 0.977 0.004

0.8

03/08/09 4,970,998.5 225.4 1,840.0 248.5 22 60.00 0.624 0.002

0.6

03/08/09 4,918,345.2 225.2 1,840.0 251.2 22 60.00 0.977 0.004

0.4

03/08/09 4,918,190.2 226.2 1,840.0 251.2 22 60.00 0.733 0.003

03/08/09 4,920,790.2 228.2 1,840.0 248.7 22 60.00 0.494 0.002
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

20:00

21:00

22:00

23:00

00:00

01:00 S S S

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 C

12:00 C

13:00 S S S

14:00 S S SC

15:00 C

16:00 C

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00 1.0

0.9

03/11/09 9,614,848.7 272.8 1,840.0 533.0 48 60.00 1.126 0.010

0.9

03/11/09 9,605,660.8 272.2 1,840.0 532.5 48 60.00 1.013 0.009

1.0

03/11/09 9,574,335.5 270.0 1,840.0 530.7 48 60.00 1.013 0.009

1.1

03/11/09 9,667,930.1 260.7 1,840.0 530.7 48 60.00 1.137 0.010

1.1

03/11/09 7,731,442.3 237.1 1,840.0 420.2 37 60.00 1.263 0.008

1.1

03/11/09 5,078,758.5 233.3 1,840.0 251.2 22 60.00 1.388 0.006

1.1

03/11/09 5,081,530.7 236.9 1,840.0 243.1 22 60.00 1.435 0.006

1.3

03/11/09 5,044,999.5 242.1 1,840.0 249.5 22 60.00 1.388 0.006

1.1

03/11/09 5,166,940.3 252.0 1,840.0 252.7 22 60.00 1.658 0.007

1.0

03/10/09 5,121,095.4 268.4 1,840.0 247.7 22 60.00 1.419 0.006

0.9

03/10/09 8,184,826.7 286.0 1,840.0 413.7 39 60.00 1.235 0.008

1.0

03/10/09 9,900,121.4 288.3 1,840.0 543.4 50 60.00 1.023 0.009

1.1

03/10/09 9,852,853.8 287.2 1,840.0 540.8 50 60.00 1.137 0.010

1.0

03/10/09 9,947,458.8 285.4 1,840.0 540.6 50 60.00 1.263 0.011

1.0

03/10/09 9,906,982.4 283.6 1,840.0 538.4 50 60.00 1.148 0.010

1.0

03/10/09 9,815,846.0 282.0 1,840.0 538.8 50 60.00 1.137 0.010

0.8

03/10/09 9,831,503.1 281.9 1,840.0 539.7 50 60.00 1.137 0.010

0.6

03/10/09 9,758,656.7 283.6 1,840.0 535.7 50 60.00 0.909 0.008

0.6

03/10/09 9,828,130.7 284.3 1,840.0 544.8 50 60.00 0.675 0.006

0.5

03/10/09 9,821,579.6 283.0 1,840.0 544.5 50 60.00 0.675 0.006

0.4

03/10/09 9,776,892.1 281.5 1,840.0 547.3 50 60.00 0.557 0.005

0.4

03/10/09 9,733,239.5 282.5 1,840.0 550.1 50 60.00 0.442 0.004

0.5

03/10/09 9,750,819.4 282.6 1,840.0 545.8 50 60.00 0.446 0.004

0.4

03/10/09 9,763,570.2 281.2 1,840.0 546.6 50 60.00 0.557 0.005

0.5

03/10/09 9,735,677.8 280.2 1,840.0 550.3 50 60.00 0.442 0.004

0.4

03/10/09 9,762,194.4 277.4 1,840.0 546.5 50 60.00 0.557 0.005

0.6

03/10/09 9,844,084.3 266.7 1,840.0 551.1 50 60.00 0.446 0.004

0.6

03/10/09 7,494,987.3 246.1 1,840.0 395.1 35 60.00 0.710 0.004

0.5

03/10/09 6,411,379.5 244.8 1,840.0 299.6 26 60.00 0.801 0.004

0.5

03/10/09 6,390,782.0 245.6 1,840.0 298.7 26 60.00 0.668 0.003

0.6

03/10/09 6,402,732.9 247.4 1,840.0 302.8 26 60.00 0.660 0.003

0.7

03/10/09 6,403,495.8 248.4 1,840.0 302.8 26 60.00 0.792 0.004

0.7

03/10/09 6,339,103.5 250.6 1,840.0 303.2 26 60.00 0.913 0.004

0.4

03/09/09 6,334,696.9 259.0 1,840.0 299.5 26 60.00 0.924 0.004

0.2

03/09/09 7,442,210.0 274.1 1,840.0 372.1 34 60.00 0.499 0.003

0.2

03/09/09 9,241,974.1 277.8 1,840.0 542.5 50 60.00 0.213 0.002

03/09/09 9,277,607.7 279.0 1,840.0 539.5 50 60.00 0.215 0.002
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 S S S

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00 0.3

0.4

03/12/09 7,730,747.5 263.8 1,840.0 432.8 40 60.00 0.334 0.002

0.4

03/12/09 8,163,626.0 264.6 1,840.0 465.9 43 60.00 0.437 0.003

0.5

03/12/09 8,063,101.7 267.5 1,840.0 464.5 43 60.00 0.433 0.003

0.4

03/12/09 8,535,946.3 273.5 1,840.0 505.7 46 60.00 0.527 0.004

0.5

03/12/09 9,263,332.0 274.8 1,840.0 558.8 51 60.00 0.414 0.004

0.5

03/12/09 9,201,720.6 274.0 1,840.0 560.1 51 60.00 0.513 0.005

0.4

03/12/09 9,102,384.4 274.0 1,840.0 559.0 51 60.00 0.508 0.005

0.3

03/12/09 9,111,515.0 273.2 1,840.0 549.7 49 60.00 0.414 0.004

0.4

03/12/09 9,086,957.6 272.3 1,840.0 538.3 49 60.00 0.316 0.003

0.5

03/12/09 8,946,691.1 272.6 1,840.0 539.7 49 60.00 0.414 0.004

0.5

03/12/09 9,146,593.0 273.0 1,840.0 546.8 50 60.00 0.522 0.005

0.3

03/12/09 9,154,921.4 272.4 1,840.0 557.3 50 60.00 0.513 0.005

0.4

03/12/09 9,106,579.6 272.7 1,840.0 549.4 50 60.00 0.310 0.003

0.4

03/12/09 9,010,604.5 273.2 1,840.0 548.5 50 60.00 0.410 0.004

0.4

03/12/09 9,139,191.8 270.9 1,840.0 561.3 50 60.00 0.406 0.004

0.4

03/12/09 8,979,988.0 266.7 1,840.0 546.6 49 60.00 0.410 0.004

0.8

03/12/09 9,103,765.4 257.8 1,840.0 549.2 49 60.00 0.414 0.004

0.6

03/12/09 7,395,602.4 232.7 1,840.0 426.1 38 60.00 0.867 0.006

0.8

03/12/09 5,028,969.6 228.7 1,840.0 248.7 22 60.00 0.757 0.003

0.7

03/12/09 4,948,577.0 233.5 1,840.0 236.7 22 60.00 1.044 0.004

0.6

03/12/09 5,025,271.0 241.2 1,840.0 251.3 22 60.00 0.874 0.004

0.4

03/12/09 5,076,556.8 255.4 1,840.0 251.1 22 60.00 0.757 0.003

0.7

03/11/09 7,324,089.7 271.0 1,840.0 402.0 38 60.00 0.455 0.003

0.7

03/11/09 9,041,319.2 274.7 1,840.0 545.4 50 60.00 0.724 0.006

0.7

03/11/09 9,088,401.2 276.5 1,840.0 548.2 50 60.00 0.724 0.006

0.7

03/11/09 9,133,331.6 276.2 1,840.0 551.0 50 60.00 0.724 0.006

0.7

03/11/09 9,073,917.3 275.5 1,840.0 547.4 50 60.00 0.724 0.006

0.8

03/11/09 9,062,160.0 276.0 1,840.0 546.7 50 60.00 0.724 0.006

1.1

03/11/09 9,234,563.4 276.2 1,840.0 542.1 50 60.00 0.850 0.007

1.4

03/11/09 9,549,590.1 276.1 1,840.0 529.4 48 60.00 1.238 0.010

1.6

03/11/09 9,563,422.0 276.2 1,840.0 535.3 48 60.00 1.561 0.013

1.1

03/11/09 9,610,487.2 277.7 1,840.0 538.0 49 60.00 1.784 0.015

1.0

03/11/09 9,628,650.2 278.2 1,840.0 533.8 48 60.00 1.238 0.011

1.2

03/11/09 9,579,564.1 278.2 1,840.0 536.3 49 60.00 1.115 0.010

1.3

03/11/09 9,616,029.4 276.3 1,840.0 538.3 48 60.00 1.338 0.012

1.2

03/11/09 9,569,294.8 274.4 1,840.0 540.9 48 60.00 1.435 0.012

03/11/09 9,581,971.7 272.8 1,840.0 536.4 48 60.00 1.338 0.011
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

22:00

23:00

00:00

01:00 C

02:00 C S S SC

03:00 C

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F 0.0 F

0.0

03/14/09 0.0 114.1 1,840.0 0.0 0 0.00 0.000 0.000

0.0

03/14/09 977.4 115.5 1,840.0 0.0 0 0.00 0.000 0.000

0.0

03/14/09 94.7 117.7 1,840.0 0.0 0 0.00 0.000 0.000

0.0

03/14/09 4,008.9 120.8 1,840.0 0.0 0 0.00 0.000 0.000

0.2

03/14/09 20,049.5 125.3 1,840.0 0.0 0 0.00 0.000 0.000

2.4

03/14/09 14,513.7 132.4 1,840.0 0.0 0 0.00 11.482 0.000

0.0

03/14/09 20,953.0 140.7 1,840.0 0.0 0 0.00 137.779 0.000

0.1

03/14/09 40,129.1 151.2 1,840.0 0.0 0 0.00 0.000 0.000

0.1

03/14/09 2,267,479.0 170.7 1,840.0 2.5 0 0.00 5.741 0.000

0.2

03/14/09 989,487.0 183.5 1,840.0 1.1 0 0.00 5.741 0.000

0.3

03/14/09 1,010,648.8 190.8 1,840.0 1.1 0 0.00 11.482 0.000

0.3

03/13/09 5,461,821.0 229.1 1,840.0 47.5 1 8.00 2.153 0.000

0.5

03/13/09 5,759,552.8 236.1 1,840.0 181.6 14 60.00 0.594 0.002

0.4

03/13/09 5,927,249.3 251.3 1,840.0 190.1 16 60.00 0.973 0.003

0.2

03/13/09 6,019,686.0 269.7 1,840.0 281.4 26 60.00 0.534 0.002

0.2

03/13/09 8,865,172.6 279.9 1,840.0 515.5 48 60.00 0.215 0.002

0.2

03/13/09 9,090,631.2 279.1 1,840.0 538.5 50 60.00 0.211 0.002

0.3

03/13/09 8,986,136.9 279.3 1,840.0 532.3 50 60.00 0.211 0.002

0.4

03/13/09 9,076,066.7 279.4 1,840.0 532.7 50 60.00 0.319 0.003

0.3

03/13/09 9,186,259.9 278.4 1,840.0 544.2 51 60.00 0.421 0.004

0.3

03/13/09 9,123,931.3 277.9 1,840.0 535.5 50 60.00 0.319 0.003

0.3

03/13/09 9,007,698.7 278.1 1,840.0 528.7 50 60.00 0.319 0.003

0.2

03/13/09 8,993,100.5 277.5 1,840.0 523.0 50 60.00 0.322 0.003

0.3

03/13/09 8,954,841.5 275.6 1,840.0 515.9 50 60.00 0.217 0.002

0.2

03/13/09 8,899,577.1 272.3 1,840.0 512.7 50 60.00 0.325 0.003

0.1

03/13/09 8,830,536.3 272.5 1,840.0 527.9 50 60.00 0.209 0.002

0.2

03/13/09 8,897,464.2 272.2 1,840.0 531.9 50 60.00 0.104 0.001

0.2

03/13/09 8,927,557.4 268.4 1,840.0 538.6 50 60.00 0.207 0.002

0.8

03/13/09 8,974,723.7 252.4 1,840.0 541.4 50 60.00 0.207 0.002

1.2

03/13/09 6,345,716.5 225.3 1,840.0 351.8 31 60.00 0.901 0.005

1.3

03/13/09 4,949,598.2 222.6 1,840.0 247.5 22 60.00 1.498 0.006

1.2

03/13/09 4,958,072.7 222.9 1,840.0 245.2 22 60.00 1.640 0.006

1.2

03/13/09 4,960,715.8 223.7 1,840.0 248.0 22 60.00 1.498 0.006

0.9

03/13/09 4,971,109.5 225.4 1,840.0 251.3 22 60.00 1.481 0.006

0.6

03/13/09 4,969,723.4 230.0 1,840.0 248.5 22 60.00 1.123 0.004

0.3

03/12/09 5,038,982.2 239.2 1,840.0 246.5 22 60.00 0.765 0.003

03/12/09 5,161,145.7 253.6 1,840.0 246.8 23 60.00 0.391 0.002
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F 0.0 F

0.0

03/15/09 635,002.7 81.0 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/15/09 620,755.3 81.6 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/15/09 620,408.0 82.2 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/15/09 590,568.2 82.8 1,840.0 0.6 0 0.00 0.000 0.000

0.0

03/15/09 575,301.2 83.1 1,840.0 0.6 0 0.00 0.000 0.000

0.0

03/15/09 553,896.9 83.8 1,840.0 0.6 0 0.00 0.000 0.000

0.0

03/15/09 573,132.7 84.9 1,840.0 0.6 0 0.00 0.000 0.000

0.0

03/15/09 638,171.8 85.9 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/15/09 630,147.2 86.5 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/15/09 663,556.4 87.1 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/15/09 666,154.4 87.7 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/15/09 661,535.7 87.8 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/15/09 662,398.6 87.5 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/15/09 623,757.1 87.1 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/15/09 626,145.4 86.7 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/15/09 504,443.7 86.5 1,840.0 0.5 0 0.00 0.000 0.000

0.0

03/15/09 486,917.2 87.1 1,840.0 0.5 0 0.00 0.000 0.000

0.2

03/15/09 450,531.4 88.1 1,840.0 0.5 0 0.00 0.000 0.000

2.4

03/15/09 386,144.3 89.4 1,840.0 0.4 0 0.00 11.482 0.000

0.0

03/15/09 463,803.7 90.0 1,840.0 0.5 0 0.00 137.779 0.000

0.0

03/15/09 418,480.2 90.5 1,840.0 0.5 0 0.00 0.000 0.000

1.8

03/15/09 2,270,473.6 91.5 1,840.0 2.5 0 0.00 0.000 0.000

0.0

03/15/09 218,071.8 92.6 1,840.0 0.2 0 0.00 103.334 0.000

0.0

03/15/09 172,499.5 93.5 1,840.0 0.2 0 0.00 0.000 0.000

0.0

03/14/09 194,019.7 94.4 1,840.0 0.2 0 0.00 0.000 0.000

0.0

03/14/09 50,271.2 95.3 1,840.0 0.1 0 0.00 0.000 0.000

0.0

03/14/09 5,269.9 96.3 1,840.0 0.0 0 0.00 0.000 0.000

0.0

03/14/09 4,175.9 97.0 1,840.0 0.0 0 0.00 0.000 0.000

0.0

03/14/09 4,627.3 98.2 1,840.0 0.0 0 0.00 0.000 0.000

0.0

03/14/09 6,383.3 100.2 1,840.0 0.0 0 0.00 0.000 0.000

0.0

03/14/09 3,379.8 102.7 1,840.0 0.0 0 0.00 0.000 0.000

0.0

03/14/09 0.0 105.0 1,840.0 0.0 0 0.00 0.000 0.000

0.0

03/14/09 0.0 107.6 1,840.0 0.0 0 0.00 0.000 0.000

0.0

03/14/09 8,383.4 110.0 1,840.0 0.0 0 0.00 0.000 0.000

0.0

03/14/09 21,504.3 111.5 1,840.0 0.0 0 0.00 0.000 0.000

0.0

03/14/09 14,443.6 112.6 1,840.0 0.0 0 0.00 0.000 0.000

03/14/09 2,682.8 113.4 1,840.0 0.0 0 0.00 0.000 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F FC

12:00 F F F F F F F F 1.5 FC

2.1

03/17/09 267,201.9 77.1 1,840.0 3.8 0 0.00 6.624 0.000

0.0

03/17/09 406,686.7 76.0 1,840.0 0.4 0 0.00 120.557 0.000

0.0

03/17/09 417,869.2 74.5 1,840.0 0.5 0 0.00 0.000 0.000

0.0

03/17/09 385,492.7 73.3 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/17/09 495,114.7 72.5 1,840.0 0.5 0 0.00 0.000 0.000

0.0

03/17/09 562,402.9 72.0 1,840.0 0.6 0 0.00 0.000 0.000

0.2

03/17/09 596,925.6 71.7 1,840.0 0.6 0 0.00 0.000 0.000

2.4

03/17/09 578,559.7 71.8 1,840.0 0.6 0 0.00 11.482 0.000

0.0

03/17/09 648,071.9 72.4 1,840.0 0.7 0 0.00 137.779 0.000

0.0

03/17/09 673,979.9 72.9 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/17/09 2,498,045.6 73.4 1,840.0 2.7 0 0.00 0.000 0.000

0.0

03/17/09 702,574.0 73.8 1,840.0 0.8 0 0.00 0.000 0.000

0.0

03/17/09 713,897.0 74.3 1,840.0 0.8 0 0.00 0.000 0.000

0.0

03/16/09 701,861.3 74.8 1,840.0 0.8 0 0.00 0.000 0.000

0.0

03/16/09 685,794.3 75.3 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/16/09 646,962.2 75.6 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/16/09 651,391.7 75.7 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/16/09 668,626.9 75.8 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/16/09 698,267.1 76.3 1,840.0 0.8 0 0.00 0.000 0.000

0.0

03/16/09 687,400.8 77.2 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/16/09 722,427.8 78.0 1,840.0 0.8 0 0.00 0.000 0.000

0.0

03/16/09 727,681.5 78.7 1,840.0 0.8 0 0.00 0.000 0.000

0.0

03/16/09 706,636.8 78.9 1,840.0 0.8 0 0.00 0.000 0.000

0.0

03/16/09 590,275.1 78.5 1,840.0 0.6 0 0.00 0.000 0.000

0.0

03/16/09 551,291.7 78.0 1,840.0 0.6 0 0.00 0.000 0.000

0.0

03/16/09 627,801.7 77.3 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/16/09 708,072.9 77.0 1,840.0 0.8 0 0.00 0.000 0.000

0.0

03/16/09 702,304.9 76.4 1,840.0 0.8 0 0.00 0.000 0.000

0.0

03/16/09 666,145.6 76.5 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/16/09 682,887.7 76.7 1,840.0 0.7 0 0.00 0.000 0.000

0.2

03/16/09 653,482.7 77.3 1,840.0 0.7 0 0.00 0.000 0.000

2.4

03/16/09 591,013.6 78.2 1,840.0 0.6 0 0.00 11.482 0.000

0.0

03/16/09 626,525.7 79.0 1,840.0 0.7 0 0.00 137.779 0.000

0.0

03/16/09 687,911.7 79.4 1,840.0 0.7 0 0.00 0.000 0.000

0.0

03/16/09 2,497,726.0 79.5 1,840.0 2.7 0 0.00 0.000 0.000

0.0

03/16/09 666,992.0 79.9 1,840.0 0.7 0 0.00 0.000 0.000

03/16/09 648,312.1 80.5 1,840.0 0.7 0 0.00 0.000 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F 0.0 F

0.0

03/19/09 752,634.8 74.0 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/19/09 732,322.5 74.7 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/18/09 709,216.5 75.5 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/18/09 701,461.3 76.2 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/18/09 682,067.5 77.0 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/18/09 623,166.9 77.6 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/18/09 588,176.2 77.9 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/18/09 533,149.1 78.3 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/18/09 487,109.7 78.8 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/18/09 481,666.5 79.0 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/18/09 455,908.0 79.0 1,840.0 0.2 0 0.00 0.000 0.000

0.0

03/18/09 388,964.6 78.6 1,840.0 0.2 0 0.00 0.000 0.000

0.0

03/18/09 274,434.9 77.9 1,840.0 0.1 0 0.00 0.000 0.000

0.0

03/18/09 385,327.3 77.3 1,840.0 0.2 0 0.00 0.000 0.000

0.0

03/18/09 464,766.2 77.1 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/18/09 454,588.8 76.8 1,840.0 0.2 0 0.00 0.000 0.000

0.0

03/18/09 447,054.1 76.7 1,840.0 0.2 0 0.00 0.000 0.000

0.0

03/18/09 595,972.5 76.8 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/18/09 674,956.4 77.2 1,840.0 0.4 0 0.00 0.000 0.000

0.2

03/18/09 698,601.7 77.8 1,840.0 0.4 0 0.00 0.000 0.000

2.4

03/18/09 686,666.3 78.8 1,840.0 0.4 0 0.00 22.963 0.000

0.0

03/18/09 665,164.5 79.5 1,840.0 0.4 0 0.00 275.558 0.000

0.0

03/18/09 693,897.5 80.2 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/18/09 2,496,902.8 81.1 1,840.0 1.4 0 0.00 0.000 0.000

0.0

03/18/09 707,707.7 81.8 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/18/09 599,333.5 82.4 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/17/09 526,732.8 82.8 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/17/09 511,039.2 83.1 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/17/09 506,041.9 83.5 1,840.0 0.6 0 0.00 0.000 0.000

0.0

03/17/09 487,534.5 83.8 1,840.0 0.5 0 0.00 0.000 0.000

0.0

03/17/09 417,877.4 83.7 1,840.0 0.5 0 0.00 0.000 0.000

0.0

03/17/09 328,363.3 83.6 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/17/09 342,224.9 83.0 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/17/09 377,636.5 81.9 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/17/09 356,063.1 80.4 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/17/09 294,076.3 78.9 1,840.0 0.3 0 0.00 0.000 0.000

03/17/09 348,265.9 78.2 1,840.0 0.4 0 0.00 0.000 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F 0.0 F

0.0

03/20/09 640,210.7 57.5 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/20/09 648,352.9 57.8 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/20/09 653,229.7 58.0 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/20/09 576,496.9 57.6 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/20/09 579,943.4 57.1 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/20/09 515,781.4 56.7 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/20/09 602,819.2 56.3 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/20/09 628,880.3 56.1 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/20/09 635,188.9 56.3 1,840.0 0.3 0 0.00 0.000 0.000

0.0

03/20/09 661,660.1 56.5 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/20/09 721,145.1 57.0 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/20/09 713,128.6 57.1 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/20/09 2,515,275.9 57.2 1,840.0 1.4 0 0.00 0.000 0.000

0.0

03/20/09 727,886.2 57.1 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/20/09 743,820.7 57.1 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/19/09 750,705.9 56.9 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/19/09 752,313.5 56.9 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/19/09 747,978.6 57.1 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/19/09 753,551.6 57.2 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/19/09 764,987.6 57.6 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/19/09 755,043.0 58.1 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/19/09 763,775.6 59.0 1,840.0 0.4 0 0.00 0.000 0.000

8.0

03/19/09 744,466.1 59.8 1,840.0 0.4 0 0.00 0.000 0.000

0.0

03/19/09 749,761.0 60.7 1,840.0 0.4 0 0.00 918.528 0.000

0.0

03/19/09 735,122.9 61.5 1,840.0 0.4 0 0.00 0.000 0.000

0.3

03/19/09 712,552.9 62.3 1,840.0 0.4 0 0.00 0.000 0.000

0.6

03/19/09 689,885.2 63.2 1,840.0 0.4 0 0.00 34.445 0.000

0.6

03/19/09 667,855.1 64.3 1,840.0 0.4 0 0.00 68.890 0.000

0.6

03/19/09 690,839.8 65.1 1,840.0 0.4 0 0.00 68.890 0.000

0.6

03/19/09 677,046.2 65.6 1,840.0 0.4 0 0.00 68.890 0.000

0.2

03/19/09 672,213.5 66.2 1,840.0 0.4 0 0.00 68.890 0.000

0.0

03/19/09 681,179.5 66.2 1,840.0 0.4 0 0.00 22.963 0.000

0.2

03/19/09 625,557.0 66.9 1,840.0 0.3 0 0.00 0.000 0.000

2.4

03/19/09 663,695.3 68.6 1,840.0 0.4 0 0.00 22.963 0.000

0.0

03/19/09 646,505.1 70.2 1,840.0 0.4 0 0.00 275.558 0.000

0.0

03/19/09 644,416.9 71.8 1,840.0 0.4 0 0.00 0.000 0.000

03/19/09 2,482,201.9 73.2 1,840.0 1.3 0 0.00 0.000 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F 0.0 F

0.0

03/22/09 499,953.7 58.1 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 2,362,399.0 58.4 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 501,762.5 58.6 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 499,902.3 58.7 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 497,808.7 59.1 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 504,383.1 59.5 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 497,737.5 59.8 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 497,581.7 59.9 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 510,723.9 60.0 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 515,335.1 60.0 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 536,841.5 60.1 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 541,690.7 60.4 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 482,859.9 60.5 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 329,517.6 60.5 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 276,527.6 60.1 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 255,784.4 59.3 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 243,459.1 58.1 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 425,856.8 56.8 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 370,919.7 55.8 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 517,531.4 55.5 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 530,944.7 55.5 1,840.0 0.0 0 0.00 0.000

0.2

03/21/09 525,203.7 55.6 1,840.0 0.0 0 0.00 0.000

2.4

03/21/09 531,083.6 55.6 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 540,482.7 55.7 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 544,140.5 55.7 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 2,407,003.2 55.9 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 557,055.5 55.9 1,840.0 0.0 0 0.00 0.000

0.0

03/21/09 562,372.6 55.8 1,840.0 0.0 0 0.00 0.000

0.0

03/20/09 557,517.3 55.8 1,840.0 0.0 0 0.00 0.000

0.0

03/20/09 559,711.4 55.9 1,840.0 0.0 0 0.00 0.000

0.0

03/20/09 560,648.3 55.8 1,840.0 0.0 0 0.00 0.000

0.0

03/20/09 557,244.3 55.7 1,840.0 0.0 0 0.00 0.000

0.0

03/20/09 587,128.0 55.8 1,840.0 0.0 0 0.00 0.000

0.0

03/20/09 600,647.5 56.1 1,840.0 0.0 0 0.00 0.000

0.0

03/20/09 627,019.0 56.7 1,840.0 0.0 0 0.00 0.000

0.0

03/20/09 632,843.2 57.0 1,840.0 0.3 0 0.00 0.000 0.000

03/20/09 647,269.5 57.2 1,840.0 0.4 0 0.00 0.000 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F 0.0 F

0.0

03/23/09 427,653.3 53.2 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 423,621.0 53.1 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 386,136.4 52.7 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 456,111.9 52.1 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 511,948.2 51.7 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 537,616.5 51.6 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 534,418.6 51.6 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 552,660.9 51.9 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 559,905.7 52.3 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 555,433.3 52.6 1,840.0 0.0 0 0.00 0.000

0.2

03/23/09 558,423.9 53.1 1,840.0 0.0 0 0.00 0.000

2.4

03/23/09 555,333.5 53.8 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 559,287.6 54.4 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 571,755.8 54.9 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 2,408,688.3 55.5 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 568,010.0 56.0 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 569,884.7 56.4 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 557,943.6 56.8 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 512,662.2 56.8 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 450,054.0 56.8 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 463,944.6 56.6 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 418,714.9 56.4 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 449,920.1 56.5 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 487,940.3 57.0 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 488,804.8 57.2 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 449,031.7 57.2 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 333,208.6 57.1 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 415,486.0 57.3 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 410,925.2 57.2 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 431,018.6 57.0 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 419,319.6 56.7 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 467,995.9 56.6 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 481,396.5 56.7 1,840.0 0.0 0 0.00 0.000

0.0

03/22/09 483,432.8 56.9 1,840.0 0.0 0 0.00 0.000

0.2

03/22/09 491,443.0 57.2 1,840.0 0.0 0 0.00 0.000

2.4

03/22/09 492,164.7 57.5 1,840.0 0.0 0 0.00 0.000

03/22/09 495,376.6 57.8 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F FC

12:00 F F F F F F F F FC

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F 0.2 FC

2.4

03/25/09 435,370.8 55.3 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 413,442.3 55.4 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 425,018.3 55.4 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 2,315,220.0 55.6 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 401,366.0 55.4 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 423,095.0 54.8 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 427,609.2 54.4 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 437,037.7 54.4 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 422,264.8 54.4 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 378,034.3 54.2 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 365,244.3 54.0 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 338,975.2 54.0 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 341,540.9 54.1 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 386,433.6 54.0 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 422,928.8 53.9 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 356,904.8 53.7 1,840.0 0.0 0 0.00 0.000

1.8

03/24/09 416,202.7 53.4 1,840.0 0.0 0 0.00 0.000

2.3

03/24/09 403,097.7 53.3 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 447,457.3 53.2 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 502,138.9 53.2 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 456,475.2 53.0 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 464,331.0 52.8 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 502,191.6 52.8 1,840.0 0.0 0 0.00 0.000

0.2

03/24/09 513,549.4 52.9 1,840.0 0.0 0 0.00 0.000

2.4

03/24/09 504,061.1 53.1 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 506,906.6 53.1 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 511,072.3 53.1 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 2,376,177.0 53.2 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 514,997.8 53.4 1,840.0 0.0 0 0.00 0.000

0.0

03/24/09 508,942.7 53.6 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 500,713.7 53.7 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 464,820.4 53.6 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 442,279.9 53.5 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 422,547.4 53.3 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 414,074.9 53.1 1,840.0 0.0 0 0.00 0.000

0.0

03/23/09 418,243.8 53.2 1,840.0 0.0 0 0.00 0.000

03/23/09 426,319.3 53.2 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F 0.0 F

0.0

03/26/09 497,122.5 58.7 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 497,961.2 59.4 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 445,760.2 60.2 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 394,765.7 60.3 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 380,585.2 60.0 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 442,819.8 59.2 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 375,654.2 58.3 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 373,258.3 57.2 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 322,495.8 56.1 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 278,835.6 55.4 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 380,701.5 54.8 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 462,980.7 54.3 1,840.0 0.0 0 0.00 0.000

0.3

03/26/09 512,360.3 54.3 1,840.0 0.0 0 0.00 0.000

2.5

03/26/09 512,669.9 54.6 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 507,679.0 54.9 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 512,514.6 55.2 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 2,373,491.9 55.5 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 519,430.2 55.6 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 509,385.9 55.6 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 504,571.7 55.6 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 507,318.8 55.5 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 498,105.7 55.6 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 500,575.0 55.8 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 502,705.5 56.0 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 495,586.6 56.3 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 469,840.4 56.4 1,840.0 0.0 0 0.00 0.000

0.2

03/25/09 468,166.7 56.5 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 386,612.0 56.6 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 359,356.1 56.3 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 335,614.7 56.1 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 323,157.8 55.8 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 395,896.3 55.7 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 409,466.1 55.8 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 425,007.7 55.7 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 412,064.6 55.5 1,840.0 0.0 0 0.00 0.000

0.0

03/25/09 405,938.7 55.3 1,840.0 1.8 0 0.00 0.000 0.000

03/25/09 420,140.5 55.2 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F 0.0 F

0.0

03/28/09 462,425.4 47.8 1,840.0 0.0 0 0.00 0.000

0.2

03/28/09 476,302.7 48.4 1,840.0 0.0 0 0.00 0.000

2.4

03/28/09 492,896.3 49.1 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 501,427.0 49.8 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 493,889.0 50.5 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 2,359,942.3 51.2 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 516,585.2 51.8 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 515,213.8 52.5 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 518,773.1 53.0 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 535,252.0 53.5 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 560,937.8 53.9 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 513,236.5 54.0 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 500,313.7 54.3 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 501,693.8 55.1 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 478,649.0 55.6 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 450,432.7 55.8 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 384,353.1 56.0 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 355,172.3 55.9 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 343,437.5 55.8 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 295,429.4 55.6 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 343,288.2 55.3 1,840.0 0.0 0 0.00 0.000

0.1

03/27/09 355,740.4 54.7 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 326,383.1 54.0 1,840.0 3.7 0 0.00 0.547 0.000

0.0

03/27/09 469,560.8 53.8 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 498,780.9 53.8 1,840.0 0.0 0 0.00 0.000

0.3

03/27/09 531,726.9 54.3 1,840.0 0.0 0 0.00 0.000

2.4

03/27/09 549,587.7 55.2 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 538,522.9 55.9 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 539,007.8 56.5 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 2,382,762.7 57.0 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 521,969.6 57.5 1,840.0 0.0 0 0.00 0.000

0.0

03/27/09 479,496.3 57.8 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 472,783.8 58.1 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 454,961.3 58.3 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 370,349.3 58.2 1,840.0 0.0 0 0.00 0.000

0.0

03/26/09 413,292.2 58.0 1,840.0 0.0 0 0.00 0.000

03/26/09 491,439.6 58.2 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 C

06:00

07:00 C

08:00 S S SC

09:00

10:00 C

11:00 C

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00 0.7

0.8

03/29/09 5,449,047.5 236.0 1,840.0 260.6 26 60.00 0.913 0.004

1.3

03/29/09 6,118,709.9 232.8 1,840.0 315.9 30 60.00 0.967 0.005

2.3

03/29/09 5,460,348.2 229.5 1,840.0 273.0 26 60.00 1.622 0.007

2.6

03/29/09 5,766,839.9 226.7 1,840.0 282.1 26 60.00 2.934 0.013

3.0

03/29/09 5,795,748.2 218.1 1,840.0 280.4 25 60.00 3.354 0.015

2.4

03/29/09 5,478,656.0 205.9 1,840.0 250.1 22 60.00 4.101 0.016

2.4

03/29/09 5,453,080.0 197.6 1,840.0 171.9 11 60.00 4.751 0.013

0.6

03/29/09 5,346,719.8 193.6 1,840.0 168.5 6 60.00 4.751 0.013

0.8

03/29/09 4,141,777.1 187.5 1,840.0 33.8 0 60.00 4.593 0.002

0.6

03/29/09 4,277,653.6 178.4 1,840.0 44.2 0 60.00 4.834 0.003

0.3

03/29/09 4,304,751.4 170.0 1,840.0 37.4 0 60.00 4.306 0.003

1.0

03/29/09 4,229,733.1 156.5 1,840.0 16.1 0 60.00 4.921 0.001

1.8

03/29/09 4,320,583.9 136.4 1,840.0 63.4 0 60.00 4.252 0.004

1.3

03/29/09 4,597,480.9 114.9 1,840.0 107.4 0 60.00 4.806 0.008

0.0

03/29/09 4,531,248.1 98.1 1,840.0 71.4 0 60.00 5.147 0.006

2.3

03/29/09 4,070,959.0 82.7 1,840.0 11.1 0 25.00 0.000 0.000

0.0

03/29/09 2,539,520.6 61.6 1,840.0 0.0 0 0.00 0.000

0.1

03/29/09 643,739.6 51.1 1,840.0 0.0 0 0.00 0.000

0.0

03/29/09 2,362,026.4 49.9 1,840.0 0.0 0 0.00 0.000

0.0

03/29/09 504,270.5 50.0 1,840.0 0.0 0 0.00 0.000

0.0

03/29/09 495,838.4 49.9 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 493,167.4 49.7 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 490,140.9 49.5 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 500,213.0 49.0 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 515,155.9 48.6 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 497,854.9 48.3 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 464,010.0 47.0 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 406,629.5 46.0 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 400,375.8 46.0 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 416,842.6 46.0 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 437,493.4 46.3 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 425,534.4 46.4 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 421,896.6 46.5 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 420,705.9 46.8 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 387,945.3 47.0 1,840.0 0.0 0 0.00 0.000

0.0

03/28/09 384,932.9 47.1 1,840.0 0.0 0 0.00 0.000

03/28/09 448,902.0 47.5 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

21:00

22:00

23:00

00:00

01:00 S S S

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 C

12:00 S S SC

13:00 C

14:00 C

15:00 C

16:00 C

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00 S S SC

09:00 0.0 C

0.0

03/31/09 8,912,310.3 257.2 1,840.0 508.6 49 60.00 0.000 0.000

0.0

03/31/09 8,225,915.5 253.1 1,840.0 496.2 49 60.00 0.000 0.000

0.1

03/31/09 8,120,140.8 245.8 1,840.0 489.8 49 60.00 0.000 0.000

0.0

03/31/09 7,440,708.7 228.4 1,840.0 440.8 42 60.00 0.105 0.001

0.1

03/31/09 5,199,507.0 222.3 1,840.0 277.0 25 60.00 0.000 0.000

0.0

03/31/09 5,186,605.2 223.6 1,840.0 279.1 25 60.00 0.116 0.001

0.1

03/31/09 5,397,501.7 225.9 1,840.0 284.6 25 60.00 0.000 0.000

0.2

03/31/09 5,430,495.2 227.5 1,840.0 286.3 26 60.00 0.118 0.001

0.3

03/31/09 5,464,793.9 230.3 1,840.0 294.0 26 60.00 0.232 0.001

0.8

03/31/09 5,469,837.0 236.0 1,840.0 291.3 26 60.00 0.351 0.002

0.8

03/30/09 5,843,019.3 247.8 1,840.0 304.9 29 60.00 0.957 0.005

1.3

03/30/09 7,392,215.7 256.1 1,840.0 458.0 45 60.00 0.806 0.006

1.6

03/30/09 8,312,966.5 262.1 1,840.0 519.6 52 60.00 1.298 0.011

1.9

03/30/09 8,850,033.6 262.3 1,840.0 553.1 55 60.00 1.597 0.014

1.6

03/30/09 8,974,141.0 260.2 1,840.0 551.1 53 60.00 1.931 0.017

1.6

03/30/09 8,190,536.7 258.5 1,840.0 503.0 49 60.00 1.626 0.013

2.0

03/30/09 8,226,304.1 259.8 1,840.0 505.2 49 60.00 1.626 0.013

2.2

03/30/09 8,260,276.4 261.7 1,840.0 498.3 49 60.00 2.069 0.016

2.4

03/30/09 8,886,746.9 262.6 1,840.0 526.5 50 60.00 2.317 0.020

2.1

03/30/09 8,815,700.5 264.0 1,840.0 517.5 50 60.00 2.551 0.021

2.1

03/30/09 9,191,195.3 266.5 1,840.0 524.5 50 60.00 2.296 0.019

2.1

03/30/09 9,213,047.1 266.5 1,840.0 555.8 50 60.00 2.172 0.019

2.0

03/30/09 9,174,474.7 266.0 1,840.0 553.4 50 60.00 2.172 0.019

1.8

03/30/09 9,083,142.3 262.1 1,840.0 557.8 51 60.00 2.032 0.018

1.2

03/30/09 9,089,957.8 256.0 1,840.0 558.2 52 60.00 1.829 0.016

0.7

03/30/09 8,781,440.4 235.6 1,840.0 501.1 47 60.00 1.312 0.011

0.6

03/30/09 5,550,083.3 217.7 1,840.0 298.6 29 60.00 0.812 0.004

0.5

03/30/09 5,092,175.3 216.7 1,840.0 260.1 26 60.00 0.733 0.003

0.4

03/30/09 5,007,429.9 215.3 1,840.0 261.2 26 60.00 0.598 0.002

0.4

03/30/09 4,883,132.2 213.2 1,840.0 246.8 24 60.00 0.494 0.002

0.5

03/30/09 4,383,263.6 213.7 1,840.0 207.2 19 60.00 0.528 0.002

0.8

03/30/09 4,303,236.0 218.2 1,840.0 196.4 19 60.00 0.683 0.002

1.1

03/30/09 4,874,407.2 223.0 1,840.0 230.5 23 60.00 1.056 0.004

0.8

03/30/09 5,255,505.1 224.3 1,840.0 262.8 26 60.00 1.373 0.006

0.5

03/29/09 5,912,020.8 223.7 1,840.0 269.9 24 60.00 1.093 0.005

0.5

03/29/09 4,600,755.2 224.9 1,840.0 210.0 20 60.00 0.683 0.002

03/29/09 4,723,134.2 230.9 1,840.0 215.6 19 60.00 0.683 0.002
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

10:00

11:00 C

12:00 C

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 S S S

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00 0.7

1.1

04/01/09 5,683,718.8 256.9 1,840.0 296.6 26 60.00 0.837 0.004

0.6

04/01/09 6,006,650.9 270.0 1,840.0 310.1 28 60.00 1.329 0.007

0.6

04/01/09 9,172,581.2 278.5 1,840.0 523.5 49 60.00 0.656 0.005

0.7

04/01/09 9,266,391.6 279.7 1,840.0 533.8 50 60.00 0.650 0.006

0.7

04/01/09 9,301,679.5 279.5 1,840.0 535.9 50 60.00 0.758 0.006

0.9

04/01/09 9,273,734.0 278.1 1,840.0 539.3 50 60.00 0.751 0.006

1.0

04/01/09 9,250,690.1 276.2 1,840.0 538.0 50 60.00 0.966 0.008

1.3

04/01/09 9,267,421.5 277.7 1,840.0 533.9 50 60.00 1.083 0.009

1.0

04/01/09 9,315,760.2 277.7 1,840.0 541.7 50 60.00 1.395 0.012

0.9

04/01/09 9,285,585.3 275.8 1,840.0 540.0 50 60.00 1.073 0.009

0.7

04/01/09 9,339,287.8 273.3 1,840.0 532.9 50 60.00 0.984 0.008

0.6

04/01/09 9,284,546.1 272.3 1,840.0 524.8 50 60.00 0.773 0.006

0.5

04/01/09 9,308,481.5 276.1 1,840.0 516.0 50 60.00 0.675 0.006

0.5

04/01/09 9,305,281.5 275.4 1,840.0 515.8 50 60.00 0.563 0.005

0.5

04/01/09 9,129,946.1 272.6 1,840.0 516.0 50 60.00 0.552 0.005

0.4

04/01/09 9,102,942.1 271.5 1,840.0 514.5 50 60.00 0.552 0.005

0.5

04/01/09 9,001,174.7 269.8 1,840.0 513.6 50 60.00 0.437 0.004

0.4

04/01/09 8,999,592.2 268.7 1,840.0 513.6 50 60.00 0.547 0.004

0.4

04/01/09 9,090,427.5 269.1 1,840.0 513.8 50 60.00 0.442 0.004

0.3

04/01/09 9,104,759.0 270.4 1,840.0 509.7 50 60.00 0.446 0.004

0.5

04/01/09 9,166,386.5 270.1 1,840.0 508.1 50 60.00 0.338 0.003

0.7

04/01/09 9,066,972.0 270.0 1,840.0 512.5 50 60.00 0.552 0.005

0.7

04/01/09 9,194,964.6 271.1 1,840.0 524.7 51 60.00 0.765 0.006

0.6

03/31/09 9,275,140.0 272.7 1,840.0 524.2 51 60.00 0.773 0.006

0.4

03/31/09 9,263,972.0 273.5 1,840.0 528.7 51 60.00 0.656 0.006

0.4

03/31/09 9,342,950.7 272.5 1,840.0 533.2 51 60.00 0.437 0.004

0.4

03/31/09 9,364,325.6 270.3 1,840.0 529.3 51 60.00 0.442 0.004

0.4

03/31/09 9,369,433.7 269.2 1,840.0 534.6 51 60.00 0.437 0.004

0.3

03/31/09 9,363,735.4 269.6 1,840.0 534.4 51 60.00 0.437 0.004

0.3

03/31/09 9,513,739.0 267.5 1,840.0 537.7 51 60.00 0.331 0.003

0.3

03/31/09 9,296,582.6 265.0 1,840.0 530.5 51 60.00 0.328 0.003

0.4

03/31/09 9,190,226.8 265.8 1,840.0 529.4 50 60.00 0.325 0.003

0.5

03/31/09 9,240,222.3 266.4 1,840.0 532.3 50 60.00 0.433 0.004

0.6

03/31/09 9,247,590.2 266.2 1,840.0 532.8 50 60.00 0.542 0.005

0.0

03/31/09 9,471,835.6 263.5 1,840.0 535.4 50 60.00 0.662 0.006

0.0

03/31/09 9,283,451.9 261.0 1,840.0 519.6 50 60.00 0.000 0.000

03/31/09 9,181,728.8 261.1 1,840.0 519.0 51 60.00 0.000 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00 M M

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 S S S

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 1.0

1.0

04/03/09 9,392,075.9 282.6 1,840.0 536.0 50 60.00 1.093 0.009

1.0

04/03/09 9,319,894.3 280.1 1,840.0 536.9 50 60.00 1.083 0.009

0.8

04/03/09 9,306,906.1 279.0 1,840.0 536.2 50 60.00 1.083 0.009

0.7

04/03/09 9,340,767.7 279.8 1,840.0 538.1 50 60.00 0.867 0.007

0.7

04/03/09 9,377,595.9 278.2 1,840.0 535.2 50 60.00 0.765 0.007

0.9

04/03/09 9,312,132.7 274.6 1,840.0 526.3 50 60.00 0.773 0.007

0.8

04/03/09 9,416,675.4 265.4 1,840.0 537.4 50 60.00 0.984 0.008

0.5

04/03/09 7,986,225.5 245.5 1,840.0 447.0 40 60.00 0.892 0.006

0.6

04/03/09 5,638,414.7 243.2 1,840.0 294.2 26 60.00 0.598 0.003

0.5

04/03/09 5,681,275.1 244.6 1,840.0 293.3 26 60.00 0.725 0.003

0.4

04/03/09 5,681,992.7 246.3 1,840.0 296.5 26 60.00 0.598 0.003

0.7

04/03/09 5,665,048.6 252.0 1,840.0 295.6 26 60.00 0.478 0.002

0.4

04/02/09 5,606,808.0 263.8 1,840.0 283.4 26 60.00 0.864 0.004

0.4

04/02/09 9,051,213.7 274.6 1,840.0 511.6 48 60.00 0.442 0.004

0.4

04/02/09 9,071,062.7 275.8 1,840.0 522.6 49 60.00 0.433 0.004

0.5

04/02/09 9,096,094.1 277.3 1,840.0 529.0 50 60.00 0.429 0.004

0.6

04/02/09 9,177,516.8 277.8 1,840.0 528.7 50 60.00 0.542 0.005

0.6

04/02/09 9,281,648.3 280.2 1,840.0 534.7 50 60.00 0.650 0.006

0.7

04/02/09 9,302,342.9 283.3 1,840.0 535.9 50 60.00 0.650 0.006

0.7

04/02/09 9,959,376.8 284.9 1,840.0 590.0 55 60.00 0.737 0.007

0.7

04/02/09 9,948,160.8 284.1 1,840.0 589.3 55 60.00 0.737 0.007

0.6

04/02/09 9,920,823.6 285.4 1,840.0 587.7 55 60.00 0.737 0.007

0.7

04/02/09 9,912,895.1 285.9 1,840.0 592.6 55 60.00 0.626 0.006

0.7

04/02/09 9,954,485.5 286.7 1,840.0 589.7 55 60.00 0.737 0.007

0.6

04/02/09 9,976,161.3 284.6 1,840.0 591.0 55 60.00 0.737 0.007

0.5

04/02/09 9,949,533.3 284.0 1,840.0 589.4 55 60.00 0.632 0.006

0.5

04/02/09 9,964,508.7 285.2 1,840.0 590.3 55 60.00 0.527 0.005

0.5

04/02/09 9,803,958.6 283.5 1,840.0 580.8 53 60.00 0.527 0.005

0.5

04/02/09 9,440,410.0 276.5 1,840.0 543.8 50 60.00 0.542 0.005

0.4

04/02/09 9,474,742.0 270.3 1,840.0 545.8 50 60.00 0.542 0.005

0.5

04/02/09 7,821,299.8 248.8 1,840.0 437.8 39 60.00 0.446 0.003

0.5

04/02/09 5,643,008.6 243.2 1,840.0 297.5 26 60.00 0.592 0.003

0.7

04/02/09 5,621,955.2 241.7 1,840.0 296.4 26 60.00 0.592 0.003

0.7

04/02/09 5,607,900.8 240.8 1,840.0 289.5 26 60.00 0.846 0.004

0.5

04/02/09 5,570,823.8 241.7 1,840.0 290.7 26 60.00 0.837 0.004

0.6

04/02/09 5,620,418.7 245.0 1,840.0 293.2 26 60.00 0.598 0.003

04/01/09 5,566,046.2 249.5 1,840.0 293.4 26 60.00 0.710 0.003
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00 0.6

0.8

04/05/09 5,777,834.4 254.1 1,840.0 285.8 25 60.00 0.757 0.003

1.0

04/04/09 6,390,999.0 269.4 1,840.0 319.6 30 60.00 0.998 0.005

1.1

04/04/09 9,383,674.2 276.3 1,840.0 535.5 50 60.00 1.093 0.009

0.9

04/04/09 9,317,762.6 275.6 1,840.0 541.9 50 60.00 1.180 0.010

1.0

04/04/09 9,407,405.8 277.7 1,840.0 547.0 50 60.00 0.966 0.008

0.9

04/04/09 9,406,681.2 278.7 1,840.0 547.0 50 60.00 1.073 0.009

1.0

04/04/09 9,365,335.2 278.7 1,840.0 539.5 50 60.00 0.975 0.008

1.0

04/04/09 9,378,504.8 278.1 1,840.0 545.4 50 60.00 1.073 0.009

0.8

04/04/09 9,381,565.4 280.3 1,840.0 545.6 50 60.00 1.073 0.009

0.8

04/04/09 9,343,530.6 282.1 1,840.0 543.4 50 60.00 0.858 0.007

0.9

04/04/09 9,368,779.7 282.8 1,840.0 544.8 50 60.00 0.858 0.007

1.1

04/04/09 9,365,066.4 283.1 1,840.0 549.7 50 60.00 0.957 0.008

1.1

04/04/09 9,340,506.7 281.9 1,840.0 548.3 50 60.00 1.169 0.010

1.2

04/04/09 9,354,312.3 279.9 1,840.0 549.0 50 60.00 1.169 0.010

1.0

04/04/09 9,341,790.7 277.8 1,840.0 548.3 50 60.00 1.276 0.011

1.0

04/04/09 9,329,635.8 277.0 1,840.0 547.6 50 60.00 1.063 0.009

1.0

04/04/09 9,376,888.3 268.2 1,840.0 555.5 50 60.00 1.053 0.009

1.6

04/04/09 7,805,293.0 241.4 1,840.0 436.9 39 60.00 1.115 0.008

2.0

04/04/09 5,282,355.2 231.3 1,840.0 252.6 22 60.00 2.088 0.008

1.4

04/04/09 5,180,068.0 230.9 1,840.0 250.6 22 60.00 2.580 0.010

1.3

04/04/09 5,220,871.8 232.9 1,840.0 252.5 22 60.00 1.806 0.007

1.3

04/04/09 5,340,312.9 235.5 1,840.0 249.6 22 60.00 1.736 0.007

1.2

04/04/09 5,326,734.5 237.3 1,840.0 257.7 22 60.00 1.677 0.007

0.8

04/04/09 5,287,972.0 240.1 1,840.0 250.0 22 60.00 1.584 0.006

1.0

04/04/09 5,281,043.3 246.5 1,840.0 249.7 22 60.00 1.056 0.004

1.2

04/03/09 5,355,432.4 259.0 1,840.0 250.3 22 60.00 1.335 0.005

1.2

04/03/09 5,925,330.7 276.3 1,840.0 276.9 26 60.00 1.602 0.007

1.2

04/03/09 9,304,203.7 285.5 1,840.0 536.0 49 60.00 1.300 0.011

1.2

04/03/09 9,351,863.6 283.7 1,840.0 543.8 50 60.00 1.288 0.011

1.0

04/03/09 9,325,877.8 282.4 1,840.0 542.3 50 60.00 1.288 0.011

1.0

04/03/09 9,331,887.7 284.3 1,840.0 537.6 50 60.00 1.083 0.009

1.1

04/03/09 9,329,687.5 284.3 1,840.0 542.6 50 60.00 1.073 0.009

1.2

04/03/09 9,313,317.8 283.9 1,840.0 541.6 50 60.00 1.180 0.010

1.0

04/03/09 9,291,825.7 282.3 1,840.0 540.4 50 60.00 1.288 0.011

1.0

04/03/09 9,277,914.7 281.4 1,840.0 539.5 50 60.00 1.073 0.009

1.0

04/03/09 9,325,309.1 283.8 1,840.0 537.2 50 60.00 1.083 0.009

04/03/09 9,345,196.3 283.8 1,840.0 538.4 50 60.00 1.083 0.009
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

01:00 S S S

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00 S S S

10:00 C

11:00 C

12:00 C

13:00 1.4 C

1.2

04/06/09 9,352,213.1 276.6 1,840.0 538.8 50 60.00 1.516 0.013

1.4

04/06/09 9,342,696.0 277.3 1,840.0 533.2 50 60.00 1.312 0.011

1.4

04/06/09 9,351,889.0 277.4 1,840.0 538.8 50 60.00 1.516 0.013

1.5

04/06/09 9,372,273.2 275.9 1,840.0 534.8 50 60.00 1.531 0.013

1.5

04/06/09 9,363,028.3 273.8 1,840.0 534.3 50 60.00 1.640 0.014

1.4

04/06/09 9,349,596.3 273.2 1,840.0 533.6 50 60.00 1.640 0.014

1.4

04/06/09 9,363,436.8 271.7 1,840.0 539.4 50 60.00 1.516 0.013

1.0

04/06/09 9,375,857.4 264.9 1,840.0 540.1 50 60.00 1.516 0.013

2.7

04/06/09 9,060,141.6 240.2 1,840.0 517.0 47 60.00 1.093 0.009

2.1

04/06/09 5,356,576.6 221.7 1,840.0 256.2 23 60.00 3.523 0.014

1.9

04/06/09 5,250,081.3 223.3 1,840.0 245.4 22 60.00 2.804 0.011

1.9

04/06/09 5,284,787.3 224.6 1,840.0 244.1 22 60.00 2.566 0.010

1.6

04/06/09 5,400,688.7 224.9 1,840.0 246.6 22 60.00 2.597 0.010

1.8

04/06/09 5,590,384.8 225.4 1,840.0 243.0 22 60.00 2.296 0.009

1.4

04/05/09 5,551,198.5 228.0 1,840.0 244.4 22 60.00 2.551 0.010

1.0

04/05/09 5,519,016.4 239.4 1,840.0 249.0 22 60.00 1.937 0.008

0.9

04/05/09 5,623,039.3 261.1 1,840.0 262.8 24 60.00 1.335 0.006

1.1

04/05/09 9,194,200.9 274.0 1,840.0 524.7 49 60.00 0.984 0.008

1.1

04/05/09 9,377,125.4 274.7 1,840.0 540.2 50 60.00 1.191 0.010

1.3

04/05/09 9,310,454.7 273.9 1,840.0 536.3 50 60.00 1.191 0.010

1.3

04/05/09 9,326,298.8 271.8 1,840.0 542.3 50 60.00 1.395 0.012

1.0

04/05/09 9,363,734.6 270.0 1,840.0 544.5 50 60.00 1.395 0.012

0.9

04/05/09 9,375,269.4 270.5 1,840.0 540.1 50 60.00 1.083 0.009

0.9

04/05/09 9,324,362.1 269.6 1,840.0 537.1 50 60.00 0.975 0.008

0.6

04/05/09 9,342,943.0 265.9 1,840.0 538.2 50 60.00 0.975 0.008

0.8

04/05/09 9,444,367.9 252.3 1,840.0 544.1 50 60.00 0.650 0.006

0.6

04/05/09 6,637,977.5 231.6 1,840.0 349.9 31 60.00 0.947 0.005

0.6

04/05/09 5,643,634.7 230.9 1,840.0 285.3 25 60.00 0.741 0.003

0.7

04/05/09 5,576,364.3 230.7 1,840.0 281.8 25 60.00 0.741 0.003

1.0

04/05/09 5,720,899.3 230.2 1,840.0 286.1 25 60.00 0.874 0.004

0.7

04/05/09 5,640,447.3 230.0 1,840.0 285.1 25 60.00 1.235 0.006

0.7

04/05/09 5,668,575.8 231.8 1,840.0 283.5 25 60.00 0.874 0.004

0.7

04/05/09 5,693,796.0 233.0 1,840.0 284.7 25 60.00 0.874 0.004

0.5

04/05/09 5,770,763.2 234.0 1,840.0 285.4 25 60.00 0.883 0.004

0.6

04/05/09 5,733,879.1 235.6 1,840.0 283.6 25 60.00 0.631 0.003

0.6

04/05/09 5,696,859.1 239.7 1,840.0 281.8 25 60.00 0.757 0.003

04/05/09 5,739,237.4 244.6 1,840.0 283.8 25 60.00 0.757 0.003
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 S S S

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 C

12:00 C

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C 0.9

0.9

04/08/09 5,176,855.5 233.3 1,840.0 247.6 23 60.00 1.174 0.005

0.6

04/08/09 5,124,655.0 236.1 1,840.0 245.1 22 60.00 1.174 0.005

0.6

04/08/09 5,146,147.2 243.4 1,840.0 246.1 22 60.00 0.783 0.003

0.6

04/07/09 5,153,696.5 255.6 1,840.0 243.7 22 60.00 0.792 0.003

0.5

04/07/09 5,736,646.3 275.1 1,840.0 268.1 25 60.00 0.801 0.003

0.6

04/07/09 9,222,166.7 284.3 1,840.0 526.3 49 60.00 0.547 0.005

0.7

04/07/09 9,221,539.0 282.7 1,840.0 531.3 50 60.00 0.650 0.006

0.5

04/07/09 9,222,060.9 281.6 1,840.0 531.3 50 60.00 0.758 0.006

0.5

04/07/09 9,209,696.7 283.1 1,840.0 525.6 50 60.00 0.547 0.005

0.6

04/07/09 9,181,049.0 283.6 1,840.0 528.9 50 60.00 0.542 0.005

0.7

04/07/09 9,061,946.3 283.1 1,840.0 522.0 49 60.00 0.650 0.005

0.9

04/07/09 9,200,304.0 283.1 1,840.0 540.0 50 60.00 0.744 0.006

0.6

04/07/09 9,227,777.7 280.5 1,840.0 536.6 50 60.00 0.966 0.008

0.7

04/07/09 9,243,793.9 280.6 1,840.0 537.6 50 60.00 0.644 0.006

0.7

04/07/09 9,222,116.4 281.0 1,840.0 536.3 50 60.00 0.751 0.006

0.7

04/07/09 9,281,957.1 280.6 1,840.0 534.7 50 60.00 0.758 0.006

0.9

04/07/09 9,225,676.5 278.6 1,840.0 531.5 50 60.00 0.758 0.006

0.8

04/07/09 9,207,802.1 276.3 1,840.0 530.5 50 60.00 0.975 0.008

0.8

04/07/09 9,240,570.1 276.2 1,840.0 532.4 50 60.00 0.867 0.007

0.8

04/07/09 9,267,268.4 273.5 1,840.0 533.9 50 60.00 0.867 0.007

0.8

04/07/09 9,066,356.1 265.7 1,840.0 527.2 50 60.00 0.858 0.007

1.1

04/07/09 8,994,473.5 247.7 1,840.0 527.9 50 60.00 0.850 0.007

1.3

04/07/09 5,923,311.6 227.1 1,840.0 305.8 28 60.00 1.329 0.007

1.1

04/07/09 5,108,480.8 227.7 1,840.0 244.3 22 60.00 1.696 0.007

1.0

04/07/09 5,107,595.2 228.3 1,840.0 249.8 22 60.00 1.403 0.006

0.9

04/07/09 5,105,438.5 230.4 1,840.0 244.2 22 60.00 1.305 0.005

1.0

04/07/09 5,106,930.4 235.0 1,840.0 244.2 22 60.00 1.174 0.005

0.9

04/06/09 5,166,834.4 242.0 1,840.0 247.1 22 60.00 1.305 0.005

1.1

04/06/09 5,237,174.8 255.2 1,840.0 250.5 22 60.00 1.174 0.005

1.1

04/06/09 6,231,074.2 272.2 1,840.0 304.8 28 60.00 1.403 0.007

1.0

04/06/09 9,314,864.8 279.1 1,840.0 536.6 50 60.00 1.191 0.010

0.9

04/06/09 9,317,759.5 279.6 1,840.0 536.8 50 60.00 1.083 0.009

0.9

04/06/09 9,344,704.2 278.6 1,840.0 533.3 50 60.00 0.984 0.008

0.9

04/06/09 9,284,777.6 276.9 1,840.0 539.9 50 60.00 0.966 0.008

0.9

04/06/09 9,258,199.7 277.3 1,840.0 533.3 50 60.00 0.975 0.008

1.2

04/06/09 9,323,823.7 278.7 1,840.0 537.1 50 60.00 0.975 0.008

04/06/09 9,362,580.6 277.7 1,840.0 539.4 50 60.00 1.300 0.011
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

03:00

04:00 C

05:00 C C

06:00

07:00 M

08:00

09:00

10:00 C

11:00 S S SC

12:00 C

13:00 C

14:00 C

15:00

16:00

17:00

18:00

19:00

20:00 C

21:00 C

22:00

23:00

00:00

01:00 S S S

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00 C

09:00 S S SC

10:00 S S SC

11:00

12:00

13:00

14:00

15:00 0.5

0.6

04/09/09 5,676,673.8 255.9 1,840.0 286.9 25 60.00 0.617 0.003

0.7

04/09/09 5,651,454.3 267.0 1,840.0 279.5 24 60.00 0.757 0.003

0.7

04/09/09 7,832,499.4 280.3 1,840.0 421.4 40 60.00 0.812 0.005

0.6

04/09/09 9,371,798.9 281.8 1,840.0 555.2 51 60.00 0.737 0.007

0.7

04/09/09 9,179,841.9 281.8 1,840.0 548.8 51 60.00 0.626 0.005

0.7

04/09/09 9,188,552.9 281.9 1,840.0 549.3 51 60.00 0.731 0.006

0.7

04/09/09 9,127,962.3 282.3 1,840.0 545.7 51 60.00 0.731 0.006

0.7

04/09/09 9,131,360.7 282.7 1,840.0 540.9 51 60.00 0.737 0.006

0.7

04/09/09 9,138,638.3 280.6 1,840.0 536.4 51 60.00 0.744 0.006

0.7

04/09/09 9,119,798.6 275.6 1,840.0 545.2 51 60.00 0.731 0.006

1.0

04/09/09 8,998,750.9 264.4 1,840.0 542.9 51 60.00 0.724 0.006

1.1

04/09/09 7,252,018.3 241.9 1,840.0 409.9 38 60.00 1.104 0.007

1.1

04/09/09 5,159,702.6 236.8 1,840.0 252.4 22 60.00 1.403 0.006

1.3

04/09/09 5,185,107.0 236.8 1,840.0 256.4 22 60.00 1.388 0.006

1.4

04/09/09 5,117,886.4 237.6 1,840.0 253.1 22 60.00 1.640 0.007

0.9

04/09/09 5,091,229.7 241.7 1,840.0 251.8 22 60.00 1.766 0.007

0.8

04/08/09 5,089,274.0 251.4 1,840.0 251.7 22 60.00 1.136 0.005

0.9

04/08/09 5,176,178.5 268.8 1,840.0 250.4 22 60.00 1.032 0.004

0.9

04/08/09 7,215,901.2 286.7 1,840.0 376.5 36 60.00 1.076 0.006

0.9

04/08/09 9,327,441.3 289.7 1,840.0 537.3 50 60.00 0.975 0.008

0.9

04/08/09 9,315,334.3 288.0 1,840.0 541.7 50 60.00 0.966 0.008

0.9

04/08/09 9,291,987.2 286.0 1,840.0 535.3 50 60.00 0.975 0.008

0.6

04/08/09 9,295,708.3 284.0 1,840.0 535.5 50 60.00 0.975 0.008

0.7

04/08/09 9,194,917.4 284.8 1,840.0 534.7 50 60.00 0.644 0.006

0.7

04/08/09 9,190,396.7 285.6 1,840.0 534.4 50 60.00 0.751 0.006

0.6

04/08/09 9,285,819.9 284.9 1,840.0 540.0 50 60.00 0.751 0.006

0.6

04/08/09 9,302,051.7 284.1 1,840.0 535.9 50 60.00 0.650 0.006

23.6

04/08/09 9,313,793.8 285.3 1,840.0 536.6 50 60.00 0.650 0.006

46.6

04/08/09 9,310,885.9 284.0 1,840.0 536.4 50 60.00 25.563 0.219

0.9

04/08/09 9,301,608.1 282.4 1,840.0 535.9 50 60.00 50.476 0.433

0.9

04/08/09 9,288,522.1 281.8 1,840.0 535.1 50 60.00 0.975 0.008

0.9

04/08/09 9,300,187.5 282.1 1,840.0 535.8 50 60.00 0.975 0.008

0.9

04/08/09 9,299,780.8 279.7 1,840.0 535.8 50 60.00 0.975 0.008

0.9

04/08/09 9,293,341.7 273.1 1,840.0 535.4 50 60.00 0.975 0.008

1.3

04/08/09 8,940,699.3 258.5 1,840.0 529.7 50 60.00 0.948 0.008

1.1

04/08/09 6,902,850.1 235.3 1,840.0 382.7 36 60.00 1.463 0.009

04/08/09 5,073,726.5 232.5 1,840.0 245.4 22 60.00 1.419 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

16:00

17:00 C

18:00 C

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00 C

09:00 C

10:00 C

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 1.4 C

1.4

04/11/09 5,354,079.8 235.9 1,840.0 279.3 25 60.00 1.674 0.007

1.4

04/11/09 5,365,602.7 238.0 1,840.0 277.0 25 60.00 1.692 0.007

1.3

04/11/09 5,554,343.3 239.2 1,840.0 280.7 25 60.00 1.728 0.008

1.7

04/11/09 5,541,019.0 237.4 1,840.0 271.0 24 60.00 1.658 0.007

1.5

04/11/09 5,310,643.4 236.7 1,840.0 262.7 23 60.00 2.145 0.009

1.0

04/10/09 5,301,672.6 240.7 1,840.0 262.2 23 60.00 1.893 0.008

0.5

04/10/09 5,369,144.5 250.4 1,840.0 262.6 23 60.00 1.276 0.005

0.6

04/10/09 5,778,472.3 265.2 1,840.0 288.9 25 60.00 0.624 0.003

0.4

04/10/09 7,568,406.3 278.0 1,840.0 403.1 37 60.00 0.703 0.005

0.5

04/10/09 9,351,494.7 272.2 1,840.0 553.9 50 60.00 0.421 0.004

0.4

04/10/09 7,104,201.5 251.2 1,840.0 405.4 37 60.00 0.547 0.004

0.4

04/10/09 5,635,116.0 250.5 1,840.0 284.8 24 60.00 0.494 0.002

0.6

04/10/09 5,691,975.1 251.2 1,840.0 284.6 24 60.00 0.499 0.002

0.6

04/10/09 5,617,643.4 254.4 1,840.0 284.0 24 60.00 0.741 0.003

0.6

04/10/09 5,607,403.7 265.7 1,840.0 280.3 24 60.00 0.749 0.003

0.6

04/10/09 7,118,284.1 282.8 1,840.0 375.2 35 60.00 0.710 0.004

0.7

04/10/09 9,294,024.2 288.8 1,840.0 545.5 50 60.00 0.638 0.006

0.6

04/10/09 9,319,022.7 288.3 1,840.0 547.0 50 60.00 0.744 0.007

0.7

04/10/09 9,255,803.4 286.5 1,840.0 543.3 50 60.00 0.638 0.006

0.6

04/10/09 9,225,928.5 283.8 1,840.0 546.5 50 60.00 0.737 0.006

0.6

04/10/09 9,221,443.3 280.6 1,840.0 546.2 50 60.00 0.632 0.006

0.4

04/10/09 9,228,849.8 276.5 1,840.0 546.7 50 60.00 0.632 0.006

0.2

04/10/09 9,260,828.7 269.4 1,840.0 543.6 50 60.00 0.425 0.004

0.3

04/10/09 7,779,168.2 247.4 1,840.0 439.7 39 60.00 0.221 0.002

0.3

04/10/09 5,638,216.7 242.0 1,840.0 291.1 25 60.00 0.363 0.002

0.3

04/10/09 5,606,317.0 241.5 1,840.0 286.4 25 60.00 0.366 0.002

0.3

04/10/09 5,610,386.4 243.6 1,840.0 283.5 25 60.00 0.370 0.002

0.4

04/10/09 5,626,922.9 245.7 1,840.0 287.5 25 60.00 0.366 0.002

0.3

04/10/09 5,643,171.5 247.6 1,840.0 288.3 25 60.00 0.489 0.002

0.5

04/09/09 5,648,129.1 251.2 1,840.0 288.5 25 60.00 0.366 0.002

0.6

04/09/09 5,674,220.9 260.1 1,840.0 286.8 25 60.00 0.617 0.003

0.5

04/09/09 6,421,853.8 278.8 1,840.0 321.1 29 60.00 0.749 0.004

0.5

04/09/09 9,285,168.6 286.8 1,840.0 545.0 50 60.00 0.532 0.005

0.2

04/09/09 9,369,432.6 277.7 1,840.0 549.9 50 60.00 0.532 0.005

0.7

04/09/09 7,779,606.5 252.4 1,840.0 439.7 39 60.00 0.221 0.002

0.5

04/09/09 5,650,655.8 247.3 1,840.0 291.8 25 60.00 0.846 0.004

04/09/09 5,671,534.1 250.7 1,840.0 289.8 25 60.00 0.611 0.003
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00 C

16:00 C

17:00 0.6

0.6

04/12/09 7,142,410.6 247.4 1,840.0 407.6 36 60.00 0.656 0.004

0.4

04/12/09 5,709,647.9 245.0 1,840.0 301.0 26 60.00 0.710 0.003

0.5

04/12/09 5,706,495.7 244.7 1,840.0 297.7 26 60.00 0.478 0.002

0.7

04/12/09 5,684,849.0 245.6 1,840.0 299.7 26 60.00 0.592 0.003

0.7

04/12/09 5,719,509.5 245.5 1,840.0 298.4 26 60.00 0.837 0.004

0.8

04/12/09 5,697,149.2 245.0 1,840.0 300.3 26 60.00 0.829 0.004

0.7

04/12/09 5,738,752.9 245.0 1,840.0 299.4 26 60.00 0.957 0.005

0.9

04/12/09 5,692,811.5 245.1 1,840.0 300.1 26 60.00 0.829 0.004

0.9

04/12/09 5,685,072.8 245.8 1,840.0 299.7 26 60.00 1.065 0.005

0.8

04/12/09 5,714,548.5 245.1 1,840.0 301.3 26 60.00 1.065 0.005

0.7

04/12/09 5,712,078.7 243.3 1,840.0 301.1 26 60.00 0.947 0.005

0.6

04/12/09 5,737,449.6 240.8 1,840.0 299.3 26 60.00 0.837 0.004

1.2

04/12/09 5,682,145.2 237.7 1,840.0 296.5 26 60.00 0.718 0.003

1.3

04/12/09 5,561,406.9 233.8 1,840.0 293.2 26 60.00 1.420 0.007

1.1

04/12/09 5,420,809.9 228.8 1,840.0 268.1 23 60.00 1.640 0.007

0.9

04/12/09 4,871,978.9 227.6 1,840.0 219.8 19 60.00 1.522 0.005

0.9

04/12/09 4,871,844.9 228.4 1,840.0 225.1 19 60.00 1.216 0.004

0.7

04/12/09 4,895,857.1 229.8 1,840.0 226.2 19 60.00 1.216 0.004

0.5

04/11/09 4,892,935.2 232.6 1,840.0 226.0 19 60.00 0.946 0.003

0.5

04/11/09 4,906,541.4 239.2 1,840.0 224.0 19 60.00 0.683 0.002

0.5

04/11/09 4,892,083.8 252.5 1,840.0 223.3 19 60.00 0.683 0.002

0.3

04/11/09 5,767,653.1 271.3 1,840.0 257.1 24 60.00 0.700 0.003

0.3

04/11/09 9,192,793.0 280.7 1,840.0 544.6 49 60.00 0.316 0.003

0.3

04/11/09 9,267,167.7 276.2 1,840.0 554.0 50 60.00 0.313 0.003

0.5

04/11/09 8,882,427.2 259.0 1,840.0 535.8 47 60.00 0.310 0.003

0.8

04/11/09 5,904,340.8 247.4 1,840.0 301.6 25 60.00 0.611 0.003

1.1

04/11/09 5,716,554.1 244.6 1,840.0 295.2 25 60.00 0.967 0.005

1.2

04/11/09 5,640,263.5 243.5 1,840.0 294.3 25 60.00 1.316 0.006

1.1

04/11/09 5,652,680.2 243.4 1,840.0 294.9 25 60.00 1.435 0.007

0.7

04/11/09 5,660,717.3 244.9 1,840.0 292.3 25 60.00 1.329 0.006

0.7

04/11/09 5,788,310.5 246.5 1,840.0 295.7 25 60.00 0.855 0.004

1.3

04/11/09 5,799,920.8 244.5 1,840.0 296.3 25 60.00 0.855 0.004

0.9

04/11/09 5,656,585.2 243.7 1,840.0 295.1 25 60.00 1.555 0.007

0.8

04/11/09 5,670,761.5 246.3 1,840.0 292.8 25 60.00 1.088 0.005

1.2

04/11/09 5,802,452.0 245.2 1,840.0 293.3 25 60.00 0.988 0.005

1.9

04/11/09 5,686,165.6 239.2 1,840.0 293.6 25 60.00 1.450 0.007

04/11/09 5,353,460.4 236.1 1,840.0 279.3 25 60.00 2.272 0.010
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00 C

10:00 S S SC

11:00 C

12:00 C

13:00 C

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00 0.7

0.7

04/14/09 9,242,111.4 275.0 1,840.0 542.5 50 60.00 0.744 0.006

0.8

04/14/09 9,262,296.9 265.2 1,840.0 543.6 50 60.00 0.744 0.006

0.8

04/14/09 7,266,708.8 245.1 1,840.0 394.9 35 60.00 0.919 0.006

1.1

04/14/09 5,814,137.8 241.8 1,840.0 287.5 25 60.00 1.009 0.005

0.7

04/14/09 5,713,083.2 242.5 1,840.0 282.5 25 60.00 1.388 0.006

0.8

04/14/09 5,786,708.1 245.7 1,840.0 286.2 25 60.00 0.883 0.004

0.7

04/14/09 5,816,243.0 249.7 1,840.0 287.6 25 60.00 1.009 0.005

0.8

04/13/09 5,899,452.8 258.1 1,840.0 288.5 25 60.00 0.893 0.004

0.5

04/13/09 6,590,626.4 272.9 1,840.0 329.6 30 60.00 0.998 0.005

0.6

04/13/09 9,100,008.4 282.0 1,840.0 534.1 49 60.00 0.532 0.005

0.6

04/13/09 9,234,462.5 282.8 1,840.0 542.0 50 60.00 0.638 0.006

0.6

04/13/09 9,268,550.1 282.0 1,840.0 544.1 50 60.00 0.638 0.006

0.6

04/13/09 9,208,383.2 282.2 1,840.0 545.5 50 60.00 0.632 0.006

0.6

04/13/09 9,221,031.8 284.0 1,840.0 546.2 50 60.00 0.632 0.006

0.7

04/13/09 9,221,430.2 284.4 1,840.0 546.2 50 60.00 0.632 0.006

0.8

04/13/09 9,202,731.2 283.5 1,840.0 545.2 50 60.00 0.737 0.006

1.0

04/13/09 9,204,898.5 281.7 1,840.0 550.3 50 60.00 0.835 0.007

0.9

04/13/09 9,236,874.7 282.8 1,840.0 547.2 50 60.00 1.053 0.009

1.0

04/13/09 9,215,385.2 283.8 1,840.0 545.9 50 60.00 0.948 0.008

1.0

04/13/09 9,219,408.5 282.7 1,840.0 551.1 50 60.00 1.044 0.009

1.0

04/13/09 9,215,930.5 280.4 1,840.0 545.9 50 60.00 1.053 0.009

0.9

04/13/09 9,179,876.1 278.3 1,840.0 548.8 50 60.00 1.044 0.009

0.8

04/13/09 9,159,036.6 279.9 1,840.0 547.5 50 60.00 0.939 0.008

0.8

04/13/09 9,205,560.0 276.6 1,840.0 550.4 50 60.00 0.835 0.007

1.2

04/13/09 9,231,727.5 264.0 1,840.0 551.9 50 60.00 0.835 0.007

0.8

04/13/09 7,145,850.0 244.6 1,840.0 396.1 35 60.00 1.351 0.009

1.0

04/13/09 5,886,184.0 244.8 1,840.0 291.1 25 60.00 1.009 0.005

1.0

04/13/09 5,911,428.3 244.6 1,840.0 292.3 25 60.00 1.262 0.006

1.3

04/13/09 5,856,876.8 243.0 1,840.0 289.7 25 60.00 1.262 0.006

1.1

04/13/09 5,776,096.0 242.9 1,840.0 291.9 25 60.00 1.605 0.007

0.8

04/13/09 5,827,961.8 245.5 1,840.0 291.4 25 60.00 1.373 0.006

1.0

04/12/09 5,875,309.0 251.9 1,840.0 290.6 25 60.00 1.009 0.005

1.0

04/12/09 5,966,112.9 261.7 1,840.0 291.8 25 60.00 1.276 0.006

1.1

04/12/09 6,684,294.1 275.6 1,840.0 341.5 31 60.00 1.221 0.007

0.9

04/12/09 9,226,570.5 279.3 1,840.0 551.6 50 60.00 1.148 0.010

0.6

04/12/09 9,203,226.2 275.2 1,840.0 550.2 50 60.00 0.939 0.008

04/12/09 9,236,116.4 267.3 1,840.0 547.1 50 60.00 0.632 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

07:00

08:00

09:00

10:00

11:00 C

12:00 C

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00 1.0

0.9

04/15/09 9,193,438.6 281.4 1,840.0 554.6 50 60.00 1.034 0.009

0.8

04/15/09 9,196,233.5 283.1 1,840.0 549.8 50 60.00 0.939 0.008

0.8

04/15/09 9,195,485.3 283.9 1,840.0 549.7 50 60.00 0.835 0.007

0.8

04/15/09 9,222,892.9 284.6 1,840.0 551.4 50 60.00 0.835 0.007

1.0

04/15/09 9,331,595.8 285.8 1,840.0 563.0 52 60.00 0.828 0.007

0.8

04/15/09 9,673,115.7 284.7 1,840.0 599.3 55 60.00 1.007 0.010

0.9

04/15/09 9,697,669.9 285.6 1,840.0 595.6 55 60.00 0.813 0.008

1.1

04/15/09 9,634,075.7 286.5 1,840.0 596.9 55 60.00 0.906 0.009

1.1

04/15/09 9,697,346.8 285.9 1,840.0 595.5 55 60.00 1.118 0.011

1.1

04/15/09 9,650,703.9 284.3 1,840.0 592.7 55 60.00 1.118 0.011

1.0

04/15/09 9,667,188.2 283.6 1,840.0 593.7 55 60.00 1.118 0.011

0.9

04/15/09 9,683,417.7 283.5 1,840.0 594.7 55 60.00 1.016 0.010

0.8

04/15/09 9,653,541.6 280.2 1,840.0 592.9 55 60.00 0.914 0.009

0.6

04/15/09 9,726,066.0 270.4 1,840.0 592.0 55 60.00 0.820 0.008

0.6

04/15/09 7,882,831.4 249.3 1,840.0 441.3 40 60.00 0.669 0.005

0.6

04/15/09 5,818,533.4 245.7 1,840.0 290.9 25 60.00 0.749 0.003

0.6

04/15/09 5,834,543.3 245.4 1,840.0 291.8 25 60.00 0.749 0.003

0.5

04/15/09 5,830,963.0 246.6 1,840.0 285.2 25 60.00 0.765 0.003

0.7

04/15/09 5,865,229.5 250.3 1,840.0 290.1 25 60.00 0.631 0.003

0.9

04/15/09 5,872,907.5 254.2 1,840.0 293.6 25 60.00 0.874 0.004

1.0

04/14/09 5,955,522.0 261.4 1,840.0 294.6 25 60.00 1.136 0.005

1.0

04/14/09 6,093,883.7 275.7 1,840.0 294.8 26 60.00 1.290 0.006

0.9

04/14/09 9,236,305.1 285.9 1,840.0 557.2 51 60.00 1.034 0.009

0.9

04/14/09 9,736,955.6 288.0 1,840.0 592.7 55 60.00 0.923 0.009

1.0

04/14/09 9,721,581.7 288.0 1,840.0 591.8 55 60.00 0.923 0.009

0.9

04/14/09 9,716,578.5 286.7 1,840.0 596.8 55 60.00 1.016 0.010

0.8

04/14/09 9,727,384.6 285.9 1,840.0 592.1 55 60.00 0.923 0.009

0.7

04/14/09 9,708,061.1 287.1 1,840.0 590.9 55 60.00 0.820 0.008

0.7

04/14/09 9,769,071.9 287.5 1,840.0 594.6 55 60.00 0.718 0.007

0.8

04/14/09 9,743,143.5 286.1 1,840.0 593.1 55 60.00 0.718 0.007

1.1

04/14/09 9,723,541.5 283.2 1,840.0 591.9 55 60.00 0.820 0.008

1.0

04/14/09 9,457,626.2 282.1 1,840.0 560.3 52 60.00 1.159 0.010

1.0

04/14/09 9,261,665.4 282.7 1,840.0 543.6 50 60.00 1.063 0.009

1.0

04/14/09 9,290,277.9 282.4 1,840.0 545.3 50 60.00 1.063 0.009

1.1

04/14/09 9,219,493.1 280.8 1,840.0 536.1 50 60.00 1.073 0.009

1.0

04/14/09 9,251,860.9 278.0 1,840.0 543.1 50 60.00 1.169 0.010

04/14/09 9,215,437.6 275.9 1,840.0 540.9 50 60.00 1.063 0.009
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00 S S 1.2 S

1.0

04/17/09 9,704,318.9 293.3 1,840.0 590.7 55 60.00 1.230 0.012

0.8

04/17/09 9,688,314.0 292.1 1,840.0 589.7 55 60.00 1.025 0.010

0.9

04/17/09 9,659,152.7 289.8 1,840.0 593.2 55 60.00 0.813 0.008

0.7

04/17/09 9,654,232.1 289.0 1,840.0 592.9 55 60.00 0.914 0.009

0.7

04/17/09 9,551,218.2 286.8 1,840.0 581.4 54 60.00 0.718 0.007

0.7

04/17/09 9,134,191.2 284.2 1,840.0 541.1 50 60.00 0.737 0.006

0.7

04/17/09 9,196,328.6 284.0 1,840.0 539.8 50 60.00 0.744 0.006

0.6

04/17/09 9,106,745.1 285.0 1,840.0 544.4 50 60.00 0.731 0.006

0.7

04/17/09 9,124,497.6 285.0 1,840.0 545.5 50 60.00 0.626 0.005

0.7

04/16/09 9,143,374.2 283.8 1,840.0 546.6 50 60.00 0.731 0.006

0.7

04/16/09 9,142,352.9 283.2 1,840.0 546.5 50 60.00 0.731 0.006

0.7

04/16/09 9,140,094.3 284.0 1,840.0 546.4 50 60.00 0.731 0.006

0.8

04/16/09 9,160,613.2 283.8 1,840.0 547.7 50 60.00 0.731 0.006

0.8

04/16/09 9,138,471.2 283.4 1,840.0 546.3 50 60.00 0.835 0.007

0.6

04/16/09 9,127,372.6 284.9 1,840.0 545.6 50 60.00 0.835 0.007

0.7

04/16/09 9,088,037.0 285.4 1,840.0 548.2 50 60.00 0.621 0.005

0.8

04/16/09 9,082,801.2 285.2 1,840.0 547.9 50 60.00 0.724 0.006

0.8

04/16/09 9,063,061.8 284.1 1,840.0 546.7 50 60.00 0.828 0.007

0.7

04/16/09 9,067,691.8 284.8 1,840.0 552.0 50 60.00 0.820 0.007

0.9

04/16/09 9,132,601.0 287.6 1,840.0 551.0 50 60.00 0.724 0.006

1.0

04/16/09 9,196,841.5 288.7 1,840.0 554.8 50 60.00 0.931 0.008

1.1

04/16/09 9,243,992.1 287.2 1,840.0 557.7 50 60.00 1.034 0.009

1.0

04/16/09 9,250,623.1 284.5 1,840.0 558.1 50 60.00 1.138 0.010

1.0

04/16/09 9,208,068.9 283.6 1,840.0 555.5 50 60.00 1.034 0.009

1.0

04/16/09 9,226,581.6 283.4 1,840.0 556.6 50 60.00 1.034 0.009

1.4

04/16/09 9,248,129.7 273.7 1,840.0 557.9 50 60.00 1.034 0.009

2.0

04/16/09 7,915,886.7 250.9 1,840.0 434.5 38 60.00 1.592 0.011

1.9

04/16/09 6,229,303.0 244.9 1,840.0 297.9 25 60.00 2.609 0.012

1.4

04/16/09 6,187,255.2 245.1 1,840.0 295.9 25 60.00 2.479 0.012

1.5

04/16/09 6,239,509.9 247.1 1,840.0 295.0 25 60.00 1.848 0.009

1.3

04/16/09 6,257,259.8 248.0 1,840.0 299.2 25 60.00 1.957 0.009

1.0

04/16/09 6,299,104.3 248.9 1,840.0 297.8 25 60.00 1.716 0.008

1.0

04/16/09 6,271,546.2 252.6 1,840.0 296.6 25 60.00 1.320 0.006

1.2

04/15/09 6,252,356.5 261.3 1,840.0 295.6 25 60.00 1.320 0.006

1.0

04/15/09 6,230,504.4 275.2 1,840.0 291.2 26 60.00 1.602 0.007

1.1

04/15/09 8,928,173.3 284.6 1,840.0 528.9 48 60.00 1.053 0.009

04/15/09 9,222,207.7 282.9 1,840.0 556.3 50 60.00 1.138 0.010
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F 0.2 F

0.2

04/18/09 2,774,067.6 199.8 1,840.0 0.0 0 0.00 0.000

0.1

04/18/09 2,631,638.5 191.5 1,840.0 0.0 0 0.00 0.000

0.0

04/18/09 2,506,313.0 183.8 1,840.0 0.0 0 0.00 0.000

0.0

04/18/09 2,408,699.5 181.3 1,840.0 0.0 0 0.00 0.000

0.1

04/18/09 2,517,970.1 184.9 1,840.0 0.0 0 0.00 0.000

0.2

04/18/09 2,516,888.7 189.5 1,840.0 0.0 0 0.00 0.000

0.4

04/18/09 2,415,353.5 191.4 1,840.0 0.0 0 0.00 0.000

0.5

04/18/09 1,852,725.3 186.8 1,840.0 0.0 0 0.00 0.000

0.4

04/18/09 1,692,471.2 185.2 1,840.0 0.0 0 0.00 0.000

0.4

04/18/09 5,295,220.4 200.5 1,840.0 103.6 9 9.00 1.276 0.000

0.6

04/18/09 4,379,429.8 203.4 1,840.0 169.0 13 60.00 0.647 0.002

0.3

04/18/09 4,395,078.3 207.9 1,840.0 167.2 13 60.00 0.984 0.003

0.3

04/18/09 5,094,339.3 212.3 1,840.0 240.9 21 60.00 0.396 0.002

0.5

04/18/09 5,388,706.7 219.0 1,840.0 260.7 23 60.00 0.387 0.002

1.2

04/18/09 5,149,056.8 234.9 1,840.0 207.1 18 60.00 0.776 0.003

1.2

04/18/09 5,234,432.7 253.5 1,840.0 193.4 17 60.00 2.026 0.006

1.3

04/18/09 7,846,457.3 261.8 1,840.0 439.2 41 60.00 1.338 0.009

1.5

04/18/09 8,026,085.9 246.8 1,840.0 449.3 41 60.00 1.449 0.010

1.5

04/18/09 5,919,791.2 243.6 1,840.0 289.6 25 60.00 1.914 0.009

1.3

04/18/09 5,919,218.3 244.0 1,840.0 292.7 25 60.00 1.893 0.009

1.4

04/18/09 5,943,322.2 244.2 1,840.0 290.7 25 60.00 1.658 0.008

1.3

04/18/09 5,913,288.9 246.0 1,840.0 289.2 25 60.00 1.786 0.008

1.3

04/17/09 5,931,665.8 250.1 1,840.0 290.2 25 60.00 1.658 0.008

1.4

04/17/09 5,946,976.8 259.6 1,840.0 287.7 25 60.00 1.677 0.008

1.5

04/17/09 6,573,247.5 278.0 1,840.0 325.1 30 60.00 1.766 0.009

1.5

04/17/09 9,662,294.9 287.5 1,840.0 588.1 55 60.00 1.538 0.014

1.4

04/17/09 9,650,917.4 288.3 1,840.0 592.7 55 60.00 1.524 0.014

1.5

04/17/09 9,619,574.0 288.2 1,840.0 590.8 55 60.00 1.422 0.013

1.4

04/17/09 9,634,588.0 286.7 1,840.0 591.7 55 60.00 1.524 0.014

1.2

04/17/09 9,644,545.2 286.6 1,840.0 592.3 55 60.00 1.422 0.013

1.2

04/17/09 9,632,544.9 285.8 1,840.0 591.6 55 60.00 1.219 0.012

1.2

04/17/09 9,660,243.3 286.1 1,840.0 588.0 55 60.00 1.230 0.012

0.7

04/17/09 9,646,549.3 285.8 1,840.0 592.5 55 60.00 1.219 0.012

1.3

04/17/09 9,659,425.7 287.3 1,840.0 593.2 55 60.00 0.711 0.007

1.4

04/17/09 9,757,631.3 289.3 1,840.0 599.3 55 60.00 1.321 0.013

1.4

04/17/09 9,733,842.9 290.0 1,840.0 597.8 55 60.00 1.422 0.014

04/17/09 9,726,092.4 290.5 1,840.0 597.3 55 60.00 1.422 0.014
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F 0.0 F

0.0

04/20/09 2,918,766.8 92.1 1,840.0 0.0 0 0.00 0.000

0.4

04/20/09 3,165,379.0 92.2 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,068,626.4 89.7 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,131,445.3 89.5 1,840.0 0.0 0 0.00 0.000

0.3

04/20/09 2,990,586.8 89.9 1,840.0 0.0 0 0.00 0.000

2.4

04/20/09 2,960,510.0 90.8 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,139,668.4 92.0 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,214,895.7 93.2 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 4,109,062.7 94.4 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,087,335.5 95.6 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,097,992.2 97.3 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 3,090,846.8 99.0 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 3,061,468.1 100.9 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,987,921.3 102.8 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,977,390.4 105.0 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,945,345.2 107.4 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,943,556.3 110.0 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 3,007,237.3 113.1 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,945,726.4 116.4 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,936,544.0 119.8 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,947,312.5 123.5 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,956,877.6 127.8 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,958,221.9 132.3 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,951,769.2 137.1 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,842,085.9 141.9 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,738,188.5 146.8 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,769,420.0 152.0 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,658,293.1 157.5 1,840.0 0.0 0 0.00 0.000

0.3

04/19/09 2,805,621.6 163.6 1,840.0 0.0 0 0.00 0.000

2.4

04/19/09 2,872,287.4 169.9 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,887,114.3 175.8 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,916,852.5 181.6 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 3,950,515.8 187.0 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,879,325.7 190.8 1,840.0 0.0 0 0.00 0.000

0.0

04/19/09 2,818,654.2 193.5 1,840.0 0.0 0 0.00 0.000

0.1

04/18/09 2,775,938.2 196.7 1,840.0 0.0 0 0.00 0.000

04/18/09 2,792,274.0 201.2 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F FC

12:00 F F F F F F F F FC

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F 0.0 F

0.0

04/21/09 2,895,361.3 74.3 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 3,000,638.8 74.4 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 2,969,613.7 74.5 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 2,896,684.8 74.4 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 2,906,810.4 74.4 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 2,958,288.1 74.6 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 2,980,734.1 74.7 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 2,955,494.2 74.7 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 2,928,969.1 74.8 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 2,859,741.8 74.8 1,840.0 0.0 0 0.00 0.000

1.4

04/21/09 2,887,084.2 74.9 1,840.0 0.0 0 0.00 0.000

2.0

04/21/09 2,872,545.4 75.1 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 2,885,637.3 75.2 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 2,907,718.7 75.4 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 2,976,836.2 75.6 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 2,943,713.9 76.0 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 2,940,230.2 76.3 1,840.0 0.0 0 0.00 0.000

0.3

04/21/09 2,916,296.3 76.8 1,840.0 0.0 0 0.00 0.000

2.4

04/21/09 2,993,484.3 77.5 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 3,036,911.2 78.0 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 3,086,217.3 78.4 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 4,101,444.5 78.3 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 3,195,327.6 77.5 1,840.0 0.0 0 0.00 0.000

0.0

04/21/09 3,404,489.7 77.3 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,394,215.5 77.5 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,383,092.1 77.1 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,500,976.7 77.1 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,379,085.6 77.7 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,310,979.7 78.4 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,443,762.9 79.3 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,404,826.3 80.1 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,387,664.6 80.8 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,409,749.4 81.7 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,434,124.3 82.7 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,297,245.1 83.8 1,840.0 0.0 0 0.00 0.000

0.0

04/20/09 3,266,142.0 86.1 1,840.0 0.0 0 0.00 0.000

04/20/09 3,104,688.5 89.3 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 C

03:00

04:00 C

05:00 S S SC

06:00

07:00 C

08:00 C ST ST

09:00 ST ST

10:00

11:00

12:00 F F F F F F F F FM

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00

17:00

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 C C

22:00 C S S SC

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 S S SC

05:00 C C

06:00

07:00

08:00 C

09:00 C

10:00 C

11:00 C

12:00 1.5 C

1.3

04/23/09 9,300,820.7 267.2 1,840.0 586.4 55 60.00 1.485 0.014

1.1

04/23/09 9,292,444.2 267.1 1,840.0 580.8 55 60.00 1.298 0.012

1.1

04/23/09 9,200,339.8 265.7 1,840.0 575.0 55 60.00 1.098 0.010

1.4

04/23/09 9,062,378.5 261.3 1,840.0 561.5 53 60.00 1.108 0.010

0.8

04/23/09 8,749,270.8 256.4 1,840.0 527.8 50 60.00 1.448 0.012

0.2

04/23/09 8,824,535.3 247.4 1,840.0 527.6 50 60.00 0.835 0.007

0.2

04/23/09 7,386,144.1 229.5 1,840.0 437.5 39 60.00 0.211 0.001

0.3

04/23/09 5,172,409.8 225.8 1,840.0 281.1 26 60.00 0.230 0.001

0.3

04/23/09 5,385,446.4 225.3 1,840.0 289.7 26 60.00 0.348 0.002

0.3

04/23/09 5,194,329.3 224.4 1,840.0 282.3 26 60.00 0.344 0.002

0.4

04/23/09 5,359,440.1 221.1 1,840.0 291.3 26 60.00 0.344 0.002

0.3

04/23/09 5,213,384.6 212.7 1,840.0 274.8 23 60.00 0.473 0.002

0.5

04/23/09 4,429,706.3 208.6 1,840.0 202.2 15 60.00 0.410 0.001

1.0

04/22/09 3,950,597.7 213.0 1,840.0 143.9 9 60.00 0.857 0.002

1.4

04/22/09 3,610,050.6 215.2 1,840.0 92.2 2 60.00 2.443 0.004

0.5

04/22/09 3,573,152.3 217.5 1,840.0 66.0 0 50.00 4.728 0.004

0.4

04/22/09 1,847,076.0 194.9 1,840.0 0.0 0 0.00 0.000

0.2

04/22/09 1,793,166.7 182.9 1,840.0 0.0 0 0.00 0.000

1.0

04/22/09 1,822,664.8 172.4 1,840.0 0.0 0 0.00 0.000

0.6

04/22/09 3,663,268.8 177.9 1,840.0 57.7 0 27.00 3.959 0.002

0.0

04/22/09 3,868,073.1 172.6 1,840.0 61.0 0 27.00 2.376 0.001

0.0

04/22/09 654,740.2 143.9 1,840.0 0.0 0 0.00 0.000

0.0

04/22/09 643,012.9 146.4 1,840.0 0.0 0 0.00 0.000

1.2

04/22/09 654,909.1 148.4 1,840.0 0.0 0 0.00 0.000

1.5

04/22/09 650,838.1 152.9 1,840.0 0.0 0 0.00 0.000

0.7

04/22/09 4,775,807.6 181.7 1,840.0 160.9 4 25.00 2.778 0.003

0.9

04/22/09 4,022,574.7 179.6 1,840.0 63.4 0 56.00 2.771 0.003

0.9

04/22/09 4,053,769.7 191.1 1,840.0 48.5 0 60.00 4.697 0.004

0.3

04/22/09 3,954,111.1 193.4 1,840.0 47.3 0 60.00 4.697 0.004

0.4

04/22/09 3,726,194.3 182.1 1,840.0 30.4 0 60.00 2.296 0.001

0.7

04/22/09 3,733,859.2 166.3 1,840.0 26.4 0 60.00 3.533 0.001

1.0

04/22/09 3,801,001.8 144.0 1,840.0 74.4 0 60.00 2.233 0.003

0.8

04/22/09 4,165,836.9 122.4 1,840.0 90.6 0 60.00 2.870 0.004

0.5

04/22/09 4,254,069.4 106.2 1,840.0 62.4 0 60.00 3.402 0.003

0.0

04/22/09 7,158,220.4 91.3 1,840.0 31.1 0 41.00 7.176 0.002

0.0

04/22/09 2,489,361.7 80.4 1,840.0 0.0 0 0.00 0.000

04/22/09 2,761,999.2 74.6 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

13:00 C

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 0.2

0.3

04/25/09 5,388,542.0 245.0 1,840.0 290.0 25 60.00 0.232 0.001

0.4

04/25/09 5,382,823.4 248.0 1,840.0 289.6 25 60.00 0.348 0.002

0.3

04/24/09 5,432,897.8 253.2 1,840.0 292.3 25 60.00 0.464 0.002

1.1

04/24/09 5,422,794.3 264.0 1,840.0 288.8 25 60.00 0.351 0.002

1.7

04/24/09 6,417,943.9 277.7 1,840.0 341.8 32 60.00 1.289 0.007

1.6

04/24/09 9,425,954.2 287.7 1,840.0 563.5 51 60.00 1.774 0.016

1.6

04/24/09 9,841,764.0 286.4 1,840.0 599.1 55 60.00 1.640 0.016

1.5

04/24/09 9,833,663.3 284.4 1,840.0 598.6 55 60.00 1.640 0.016

1.6

04/24/09 9,827,210.6 283.2 1,840.0 592.8 55 60.00 1.552 0.015

1.8

04/24/09 9,847,421.9 280.8 1,840.0 599.4 55 60.00 1.640 0.016

1.6

04/24/09 9,822,564.6 277.1 1,840.0 597.9 55 60.00 1.845 0.018

1.5

04/24/09 9,858,210.6 273.0 1,840.0 589.3 55 60.00 1.670 0.016

1.2

04/24/09 9,343,372.7 268.4 1,840.0 573.8 55 60.00 1.524 0.014

1.0

04/24/09 9,355,768.2 263.2 1,840.0 569.5 54 60.00 1.230 0.011

0.4

04/24/09 8,789,392.0 253.2 1,840.0 520.7 50 60.00 1.053 0.009

0.5

04/24/09 7,188,553.5 230.6 1,840.0 406.3 40 60.00 0.442 0.003

0.5

04/24/09 4,917,663.7 225.2 1,840.0 264.6 24 60.00 0.580 0.002

0.6

04/24/09 4,939,710.0 225.7 1,840.0 265.8 24 60.00 0.580 0.002

0.6

04/24/09 4,849,416.5 227.4 1,840.0 260.9 24 60.00 0.696 0.003

0.6

04/24/09 4,870,693.0 227.4 1,840.0 262.1 24 60.00 0.696 0.003

0.6

04/24/09 4,869,976.0 227.3 1,840.0 262.0 24 60.00 0.696 0.003

0.7

04/24/09 4,889,486.0 227.4 1,840.0 263.0 24 60.00 0.696 0.003

0.8

04/24/09 4,885,805.4 228.2 1,840.0 262.9 24 60.00 0.812 0.003

0.7

04/24/09 4,966,244.5 229.8 1,840.0 261.8 24 60.00 0.947 0.004

1.1

04/24/09 4,951,817.1 233.1 1,840.0 263.7 24 60.00 0.820 0.003

1.1

04/24/09 5,210,629.3 239.4 1,840.0 274.7 24 60.00 1.302 0.006

1.2

04/23/09 5,388,451.8 248.8 1,840.0 275.3 24 60.00 1.344 0.006

1.5

04/23/09 6,086,972.3 263.8 1,840.0 314.3 29 60.00 1.450 0.007

1.5

04/23/09 9,386,094.9 271.0 1,840.0 581.5 55 60.00 1.511 0.014

1.6

04/23/09 9,366,842.6 272.1 1,840.0 585.4 55 60.00 1.498 0.014

1.7

04/23/09 9,318,584.2 272.8 1,840.0 587.5 55 60.00 1.584 0.015

1.6

04/23/09 9,366,813.3 271.5 1,840.0 585.4 55 60.00 1.697 0.016

1.7

04/23/09 9,334,386.2 270.9 1,840.0 588.4 55 60.00 1.584 0.015

1.6

04/23/09 9,364,162.7 271.5 1,840.0 585.3 55 60.00 1.697 0.016

1.6

04/23/09 9,358,818.1 270.4 1,840.0 584.9 55 60.00 1.597 0.015

1.5

04/23/09 9,299,311.2 268.8 1,840.0 586.2 55 60.00 1.584 0.015

04/23/09 9,266,075.5 267.7 1,840.0 584.2 55 60.00 1.485 0.014
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00 1.3

1.4

04/26/09 5,777,435.4 235.2 1,840.0 298.3 25 60.00 1.571 0.007

1.1

04/26/09 5,779,237.7 234.6 1,840.0 298.4 25 60.00 1.692 0.008

1.0

04/26/09 5,799,901.2 233.1 1,840.0 299.5 25 60.00 1.329 0.006

1.2

04/26/09 5,733,261.8 232.7 1,840.0 299.1 25 60.00 1.196 0.006

1.2

04/26/09 5,789,696.7 233.4 1,840.0 298.9 25 60.00 1.450 0.007

1.1

04/26/09 5,807,154.4 232.1 1,840.0 299.8 25 60.00 1.450 0.007

1.0

04/26/09 5,810,841.2 230.3 1,840.0 300.0 25 60.00 1.329 0.006

1.0

04/26/09 5,777,499.8 229.2 1,840.0 298.3 25 60.00 1.209 0.006

1.1

04/26/09 5,721,681.7 230.1 1,840.0 295.4 25 60.00 1.209 0.006

0.8

04/26/09 5,791,781.6 229.6 1,840.0 299.0 25 60.00 1.329 0.006

0.7

04/26/09 5,814,549.6 228.4 1,840.0 300.2 25 60.00 0.967 0.005

0.9

04/26/09 5,773,080.5 228.4 1,840.0 298.1 25 60.00 0.846 0.004

1.0

04/26/09 5,800,929.6 231.2 1,840.0 296.4 25 60.00 1.099 0.005

0.9

04/26/09 5,813,425.7 233.7 1,840.0 297.0 25 60.00 1.221 0.006

0.7

04/26/09 5,850,401.5 237.8 1,840.0 298.9 25 60.00 1.099 0.005

0.6

04/25/09 5,849,902.8 246.9 1,840.0 298.9 25 60.00 0.855 0.004

0.9

04/25/09 6,345,754.7 262.7 1,840.0 327.6 29 60.00 0.725 0.004

1.3

04/25/09 8,825,830.2 274.5 1,840.0 518.0 47 60.00 0.957 0.008

1.3

04/25/09 9,591,223.2 278.7 1,840.0 589.0 54 60.00 1.321 0.012

1.6

04/25/09 9,784,414.6 277.1 1,840.0 606.2 55 60.00 1.309 0.013

1.2

04/25/09 9,778,281.9 269.0 1,840.0 605.8 55 60.00 1.611 0.016

1.6

04/25/09 9,432,308.5 242.4 1,840.0 579.2 51 60.00 1.219 0.011

1.3

04/25/09 5,147,802.0 223.3 1,840.0 271.4 23 60.00 1.894 0.008

0.9

04/25/09 4,980,880.3 226.7 1,840.0 251.8 22 60.00 1.605 0.006

0.6

04/25/09 4,995,366.2 235.8 1,840.0 249.8 22 60.00 1.123 0.004

0.9

04/25/09 5,045,503.5 253.3 1,840.0 244.1 22 60.00 0.774 0.003

1.1

04/25/09 8,028,315.5 268.7 1,840.0 458.1 43 60.00 0.984 0.007

1.1

04/25/09 9,438,786.1 271.0 1,840.0 564.3 51 60.00 1.148 0.010

1.1

04/25/09 9,444,709.2 270.5 1,840.0 559.5 51 60.00 1.159 0.010

1.0

04/25/09 9,570,159.7 272.0 1,840.0 577.3 52 60.00 1.138 0.011

0.4

04/25/09 9,722,322.7 267.6 1,840.0 597.1 55 60.00 1.016 0.010

0.3

04/25/09 8,977,762.4 247.5 1,840.0 541.6 48 60.00 0.414 0.004

0.5

04/25/09 5,425,922.2 237.3 1,840.0 294.9 25 60.00 0.344 0.002

0.4

04/25/09 5,430,618.3 239.0 1,840.0 295.2 25 60.00 0.574 0.003

0.3

04/25/09 5,433,766.8 241.0 1,840.0 292.4 25 60.00 0.464 0.002

0.3

04/25/09 5,455,124.3 242.2 1,840.0 293.5 25 60.00 0.348 0.002

04/25/09 5,482,747.8 242.9 1,840.0 295.0 25 60.00 0.348 0.002
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00 0.1

0.1

04/28/09 5,493,715.7 231.5 1,840.0 301.6 25 60.00 0.114 0.001

0.1

04/28/09 5,486,860.1 233.3 1,840.0 301.2 25 60.00 0.114 0.001

0.1

04/28/09 5,522,631.4 238.2 1,840.0 300.2 25 60.00 0.115 0.001

0.0

04/28/09 5,574,652.7 245.5 1,840.0 300.0 25 60.00 0.116 0.001

0.0

04/27/09 5,687,922.5 258.0 1,840.0 302.9 25 60.00 0.000 0.000

0.3

04/27/09 7,283,702.0 273.8 1,840.0 391.9 36 60.00 0.000 0.000

0.2

04/27/09 9,361,192.7 277.4 1,840.0 564.7 50 60.00 0.310 0.003

0.2

04/27/09 9,421,473.4 279.4 1,840.0 568.3 50 60.00 0.207 0.002

0.3

04/27/09 9,447,421.5 280.9 1,840.0 569.9 50 60.00 0.207 0.002

0.3

04/27/09 9,491,895.5 281.2 1,840.0 567.5 50 60.00 0.313 0.003

0.4

04/27/09 9,531,654.9 281.2 1,840.0 569.8 50 60.00 0.313 0.003

0.3

04/27/09 9,543,468.0 282.3 1,840.0 565.3 50 60.00 0.421 0.004

0.4

04/27/09 9,507,695.3 282.5 1,840.0 563.2 50 60.00 0.316 0.003

0.4

04/27/09 9,570,331.4 281.9 1,840.0 561.7 50 60.00 0.425 0.004

0.5

04/27/09 9,541,355.7 280.6 1,840.0 560.0 50 60.00 0.425 0.004

0.3

04/27/09 9,562,832.8 280.9 1,840.0 566.5 50 60.00 0.527 0.005

0.1

04/27/09 9,578,247.7 279.2 1,840.0 567.4 50 60.00 0.316 0.003

0.4

04/27/09 9,390,173.8 273.9 1,840.0 556.3 49 60.00 0.105 0.001

0.2

04/27/09 9,346,837.4 265.4 1,840.0 558.8 50 60.00 0.418 0.004

0.1

04/27/09 7,981,789.9 243.8 1,840.0 472.8 41 60.00 0.211 0.002

0.1

04/27/09 5,575,795.5 237.0 1,840.0 294.0 25 60.00 0.118 0.001

0.2

04/27/09 5,498,814.1 236.0 1,840.0 289.9 25 60.00 0.118 0.001

0.1

04/27/09 5,610,025.2 237.1 1,840.0 289.6 25 60.00 0.242 0.001

0.2

04/27/09 5,495,538.9 237.2 1,840.0 292.7 25 60.00 0.117 0.001

0.2

04/27/09 5,474,678.3 236.4 1,840.0 288.6 25 60.00 0.237 0.001

0.3

04/27/09 5,448,161.7 237.9 1,840.0 290.2 25 60.00 0.234 0.001

0.3

04/27/09 5,469,151.8 240.5 1,840.0 291.3 25 60.00 0.351 0.002

0.3

04/27/09 5,469,696.4 243.7 1,840.0 291.3 25 60.00 0.351 0.002

0.3

04/26/09 5,495,924.9 251.4 1,840.0 289.7 25 60.00 0.355 0.002

0.7

04/26/09 5,570,072.4 267.6 1,840.0 287.6 26 60.00 0.363 0.002

0.7

04/26/09 9,349,342.0 280.1 1,840.0 564.0 51 60.00 0.724 0.007

0.6

04/26/09 9,860,668.8 278.6 1,840.0 605.6 55 60.00 0.711 0.007

0.5

04/26/09 9,856,584.4 267.1 1,840.0 605.3 55 60.00 0.610 0.006

1.2

04/26/09 7,676,437.7 239.1 1,840.0 442.2 38 60.00 0.542 0.004

1.5

04/26/09 5,576,025.9 232.6 1,840.0 294.0 25 60.00 1.420 0.007

1.2

04/26/09 5,728,154.9 232.4 1,840.0 295.7 25 60.00 1.813 0.009

04/26/09 5,720,401.3 234.0 1,840.0 298.4 25 60.00 1.435 0.007
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 C

12:00 C

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00 0.8

0.8

04/29/09 9,979,381.6 281.5 1,840.0 607.4 55 60.00 0.820 0.008

0.8

04/29/09 9,950,383.0 281.8 1,840.0 611.1 55 60.00 0.813 0.008

0.6

04/29/09 9,893,576.5 281.4 1,840.0 602.2 54 60.00 0.820 0.008

0.6

04/29/09 9,936,536.7 280.4 1,840.0 610.3 55 60.00 0.610 0.006

0.5

04/29/09 9,949,461.4 280.8 1,840.0 611.0 55 60.00 0.610 0.006

0.6

04/29/09 9,839,670.7 279.7 1,840.0 609.7 54 60.00 0.504 0.005

0.6

04/29/09 9,800,958.2 277.3 1,840.0 607.2 55 60.00 0.604 0.006

0.6

04/29/09 9,675,296.5 276.5 1,840.0 609.9 55 60.00 0.594 0.006

0.5

04/29/09 9,883,075.6 277.8 1,840.0 617.7 56 60.00 0.599 0.006

0.6

04/29/09 9,798,997.1 276.2 1,840.0 612.4 55 60.00 0.499 0.005

0.7

04/29/09 9,474,480.0 271.5 1,840.0 576.7 51 60.00 0.615 0.006

0.7

04/29/09 8,815,047.3 268.7 1,840.0 512.6 45 60.00 0.751 0.006

0.8

04/29/09 8,744,821.3 269.9 1,840.0 508.5 45 60.00 0.751 0.006

0.8

04/29/09 8,711,060.1 270.4 1,840.0 506.6 45 60.00 0.858 0.007

0.8

04/29/09 8,748,902.0 270.1 1,840.0 504.0 45 60.00 0.867 0.007

0.8

04/29/09 8,719,835.2 269.2 1,840.0 511.8 45 60.00 0.850 0.007

0.8

04/29/09 8,657,625.9 268.1 1,840.0 508.2 45 60.00 0.850 0.007

0.6

04/28/09 8,719,827.3 270.2 1,840.0 507.1 45 60.00 0.858 0.007

0.7

04/28/09 8,733,055.3 271.9 1,840.0 512.6 45 60.00 0.638 0.005

0.6

04/28/09 8,823,965.6 271.7 1,840.0 522.7 45 60.00 0.737 0.006

0.6

04/28/09 8,864,260.3 269.4 1,840.0 525.1 45 60.00 0.632 0.005

0.5

04/28/09 8,774,468.0 267.3 1,840.0 519.8 45 60.00 0.632 0.005

0.5

04/28/09 8,776,202.6 269.1 1,840.0 519.9 45 60.00 0.527 0.004

0.5

04/28/09 8,786,447.4 269.6 1,840.0 520.5 45 60.00 0.527 0.004

0.5

04/28/09 8,836,261.2 269.3 1,840.0 523.4 45 60.00 0.527 0.004

0.6

04/28/09 8,778,598.6 270.3 1,840.0 520.1 45 60.00 0.527 0.004

0.7

04/28/09 9,373,106.7 274.3 1,840.0 565.4 50 60.00 0.621 0.006

0.7

04/28/09 9,385,432.0 275.8 1,840.0 571.3 50 60.00 0.718 0.007

0.7

04/28/09 9,692,343.8 277.6 1,840.0 605.8 53 60.00 0.699 0.007

0.6

04/28/09 9,905,523.8 277.2 1,840.0 624.5 55 60.00 0.693 0.007

0.6

04/28/09 9,902,639.1 278.3 1,840.0 618.9 55 60.00 0.599 0.006

0.5

04/28/09 9,917,505.6 277.8 1,840.0 625.3 55 60.00 0.594 0.006

0.5

04/28/09 9,935,361.6 275.7 1,840.0 620.9 55 60.00 0.499 0.005

0.2

04/28/09 9,861,723.2 272.8 1,840.0 616.4 55 60.00 0.499 0.005

0.1

04/28/09 9,841,150.1 268.9 1,840.0 620.4 55 60.00 0.198 0.002

0.0

04/28/09 9,627,200.6 250.0 1,840.0 596.5 52 60.00 0.101 0.001

04/28/09 5,762,364.5 232.1 1,840.0 319.4 26 60.00 0.000 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C 0.2 C

0.0

05/01/09 9,411,580.7 253.6 1,840.0 562.7 49 60.00 0.209 0.002

0.0

05/01/09 5,682,140.8 237.2 1,840.0 302.6 25 60.00 0.000 0.000

0.0

05/01/09 5,236,598.8 238.3 1,840.0 264.7 22 60.00 0.000 0.000

0.0

05/01/09 5,211,768.3 242.8 1,840.0 263.4 22 60.00 0.000 0.000

0.0

05/01/09 5,251,413.8 247.1 1,840.0 265.4 22 60.00 0.000 0.000

0.1

05/01/09 5,348,920.7 256.1 1,840.0 270.4 22 60.00 0.000 0.000

0.4

04/30/09 5,326,270.2 271.1 1,840.0 260.5 23 60.00 0.128 0.001

0.4

04/30/09 9,169,464.7 283.3 1,840.0 533.2 49 60.00 0.429 0.004

0.3

04/30/09 9,945,506.7 284.2 1,840.0 600.0 55 60.00 0.414 0.004

0.3

04/30/09 9,945,933.5 285.0 1,840.0 600.0 55 60.00 0.310 0.003

0.3

04/30/09 9,906,780.0 284.8 1,840.0 603.0 55 60.00 0.308 0.003

0.3

04/30/09 9,860,451.4 283.7 1,840.0 600.2 55 60.00 0.308 0.003

0.3

04/30/09 9,875,485.2 283.5 1,840.0 601.1 55 60.00 0.308 0.003

0.3

04/30/09 9,872,649.4 284.5 1,840.0 601.0 55 60.00 0.308 0.003

0.4

04/30/09 9,882,260.6 283.8 1,840.0 601.5 55 60.00 0.308 0.003

0.4

04/30/09 9,874,646.6 282.0 1,840.0 601.1 55 60.00 0.410 0.004

0.4

04/30/09 9,846,159.2 281.0 1,840.0 599.3 55 60.00 0.410 0.004

0.5

04/30/09 9,818,754.4 281.4 1,840.0 603.0 55 60.00 0.406 0.004

0.5

04/30/09 9,803,830.9 280.9 1,840.0 602.1 55 60.00 0.508 0.005

0.5

04/30/09 9,808,104.0 279.2 1,840.0 602.3 55 60.00 0.508 0.005

0.5

04/30/09 9,548,758.4 274.0 1,840.0 576.1 52 60.00 0.517 0.005

0.4

04/30/09 9,281,922.1 272.9 1,840.0 549.9 50 60.00 0.527 0.005

0.4

04/30/09 9,265,934.7 272.7 1,840.0 553.9 50 60.00 0.418 0.004

0.2

04/30/09 9,317,861.6 267.2 1,840.0 557.1 50 60.00 0.418 0.004

0.2

04/30/09 9,143,646.9 247.8 1,840.0 541.7 48 60.00 0.211 0.002

0.2

04/30/09 5,481,829.1 234.8 1,840.0 289.0 24 60.00 0.237 0.001

0.2

04/30/09 5,217,598.4 235.4 1,840.0 266.6 22 60.00 0.244 0.001

0.2

04/30/09 5,257,592.5 236.5 1,840.0 265.8 22 60.00 0.247 0.001

0.3

04/30/09 5,251,209.2 239.2 1,840.0 265.4 22 60.00 0.247 0.001

0.4

04/30/09 5,238,584.0 246.2 1,840.0 264.8 22 60.00 0.370 0.002

0.5

04/29/09 5,167,035.0 258.8 1,840.0 255.5 22 60.00 0.505 0.002

0.5

04/29/09 7,838,170.9 272.9 1,840.0 434.5 40 60.00 0.563 0.004

0.4

04/29/09 9,116,687.9 273.4 1,840.0 550.0 50 60.00 0.517 0.005

0.4

04/29/09 9,144,149.7 274.6 1,840.0 551.6 50 60.00 0.414 0.004

0.4

04/29/09 9,175,019.6 275.3 1,840.0 543.5 50 60.00 0.421 0.004

0.6

04/29/09 9,135,344.6 276.2 1,840.0 541.1 50 60.00 0.421 0.004

04/29/09 9,261,309.9 279.1 1,840.0 558.7 51 60.00 0.621 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00 0.3

0.2

05/02/09 9,970,132.6 263.6 1,840.0 601.5 54 60.00 0.310 0.003

0.1

05/02/09 6,796,141.7 239.8 1,840.0 373.0 33 60.00 0.227 0.001

0.0

05/02/09 5,278,698.7 238.4 1,840.0 281.2 24 60.00 0.117 0.001

0.0

05/02/09 5,282,922.5 237.5 1,840.0 281.4 24 60.00 0.000 0.000

0.1

05/02/09 5,302,069.9 237.3 1,840.0 282.4 24 60.00 0.000 0.000

0.1

05/02/09 5,398,467.1 237.2 1,840.0 284.6 24 60.00 0.118 0.001

0.1

05/02/09 5,275,407.0 236.8 1,840.0 278.1 24 60.00 0.118 0.001

0.2

05/02/09 5,275,452.0 237.7 1,840.0 275.2 24 60.00 0.120 0.001

0.2

05/02/09 5,433,157.6 239.1 1,840.0 286.4 25 60.00 0.237 0.001

0.3

05/02/09 5,356,373.0 238.9 1,840.0 285.3 24 60.00 0.234 0.001

0.2

05/02/09 5,372,882.9 237.5 1,840.0 283.3 24 60.00 0.355 0.002

0.3

05/02/09 5,398,995.3 235.7 1,840.0 284.6 24 60.00 0.237 0.001

0.3

05/02/09 5,320,982.0 234.6 1,840.0 283.4 24 60.00 0.351 0.002

0.2

05/02/09 5,332,186.5 236.3 1,840.0 281.1 24 60.00 0.355 0.002

0.2

05/02/09 5,382,347.2 237.2 1,840.0 283.7 24 60.00 0.237 0.001

0.1

05/02/09 5,419,782.0 236.8 1,840.0 282.8 24 60.00 0.239 0.001

0.2

05/02/09 5,359,221.7 236.8 1,840.0 273.8 24 60.00 0.122 0.001

0.2

05/02/09 5,374,160.5 238.3 1,840.0 283.3 24 60.00 0.237 0.001

0.2

05/02/09 5,395,160.1 239.2 1,840.0 284.4 24 60.00 0.237 0.001

0.1

05/01/09 5,389,103.6 240.7 1,840.0 284.1 24 60.00 0.237 0.001

0.2

05/01/09 5,443,500.4 244.6 1,840.0 287.0 24 60.00 0.118 0.001

0.4

05/01/09 5,390,435.2 251.5 1,840.0 284.1 24 60.00 0.237 0.001

0.4

05/01/09 6,441,096.1 258.0 1,840.0 350.1 32 60.00 0.459 0.003

0.4

05/01/09 7,044,397.5 258.9 1,840.0 390.5 35 60.00 0.450 0.003

0.5

05/01/09 7,020,948.9 258.8 1,840.0 389.2 35 60.00 0.450 0.003

0.5

05/01/09 7,074,738.2 260.8 1,840.0 392.2 35 60.00 0.563 0.004

0.5

05/01/09 7,041,444.3 261.3 1,840.0 394.1 35 60.00 0.557 0.004

0.6

05/01/09 7,106,745.3 261.0 1,840.0 394.0 35 60.00 0.563 0.004

0.7

05/01/09 7,078,258.1 259.4 1,840.0 392.4 35 60.00 0.675 0.004

0.6

05/01/09 7,091,833.0 257.8 1,840.0 393.1 35 60.00 0.788 0.005

0.6

05/01/09 7,045,348.0 257.2 1,840.0 394.4 35 60.00 0.669 0.004

0.5

05/01/09 7,066,835.3 256.8 1,840.0 391.8 35 60.00 0.675 0.004

0.4

05/01/09 7,039,967.2 259.0 1,840.0 390.3 35 60.00 0.563 0.004

0.3

05/01/09 7,027,749.7 261.5 1,840.0 389.6 35 60.00 0.450 0.003

0.4

05/01/09 7,281,694.8 267.3 1,840.0 403.7 36 60.00 0.338 0.002

0.4

05/01/09 8,748,626.1 272.8 1,840.0 518.3 46 60.00 0.421 0.003

05/01/09 9,351,982.1 270.4 1,840.0 559.1 50 60.00 0.418 0.004
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00 0.4

0.2

05/04/09 9,970,522.1 273.8 1,840.0 606.9 55 60.00 0.410 0.004

0.2

05/04/09 9,394,978.0 253.4 1,840.0 561.7 49 60.00 0.209 0.002

0.2

05/04/09 5,685,707.7 242.0 1,840.0 309.0 26 60.00 0.230 0.001

0.2

05/04/09 5,690,461.2 242.8 1,840.0 303.1 26 60.00 0.234 0.001

0.3

05/04/09 5,744,083.4 242.3 1,840.0 305.9 26 60.00 0.234 0.001

0.5

05/04/09 5,717,093.2 242.0 1,840.0 313.8 26 60.00 0.341 0.002

0.4

05/04/09 5,771,861.5 243.1 1,840.0 304.3 26 60.00 0.592 0.003

0.4

05/04/09 5,793,256.5 246.1 1,840.0 299.1 25 60.00 0.483 0.002

0.3

05/03/09 5,712,941.0 250.2 1,840.0 291.9 24 60.00 0.489 0.002

0.4

05/03/09 5,646,610.7 261.7 1,840.0 285.4 24 60.00 0.370 0.002

0.4

05/03/09 7,246,311.7 277.8 1,840.0 382.0 35 60.00 0.473 0.003

0.4

05/03/09 10,008,052.2 283.7 1,840.0 603.7 55 60.00 0.414 0.004

0.3

05/03/09 9,971,966.9 281.9 1,840.0 601.6 55 60.00 0.414 0.004

0.2

05/03/09 9,992,489.8 274.5 1,840.0 608.2 55 60.00 0.308 0.003

0.5

05/03/09 9,066,425.8 248.9 1,840.0 542.0 48 60.00 0.209 0.002

0.4

05/03/09 5,595,087.2 238.0 1,840.0 295.0 25 60.00 0.592 0.003

0.3

05/03/09 5,597,630.1 240.0 1,840.0 292.1 25 60.00 0.478 0.002

0.3

05/03/09 5,622,758.6 241.2 1,840.0 293.4 25 60.00 0.359 0.002

0.3

05/03/09 5,634,696.6 240.9 1,840.0 294.0 25 60.00 0.359 0.002

0.6

05/03/09 5,671,444.5 239.7 1,840.0 295.9 25 60.00 0.359 0.002

0.6

05/03/09 5,591,277.6 238.1 1,840.0 294.7 25 60.00 0.710 0.003

0.5

05/03/09 5,629,293.6 237.7 1,840.0 296.7 25 60.00 0.710 0.003

0.4

05/03/09 5,612,603.5 238.3 1,840.0 292.9 25 60.00 0.598 0.003

0.3

05/03/09 5,680,487.4 238.3 1,840.0 296.3 25 60.00 0.478 0.002

0.3

05/03/09 5,658,868.0 235.4 1,840.0 295.3 25 60.00 0.359 0.002

0.3

05/03/09 5,664,348.5 230.6 1,840.0 295.5 25 60.00 0.359 0.002

0.3

05/03/09 5,433,113.5 226.0 1,840.0 277.6 23 60.00 0.366 0.002

0.2

05/03/09 4,766,601.1 225.2 1,840.0 228.0 19 60.00 0.391 0.001

0.2

05/03/09 4,732,767.7 226.0 1,840.0 226.4 19 60.00 0.261 0.001

0.2

05/03/09 4,733,930.7 228.2 1,840.0 231.6 19 60.00 0.255 0.001

0.2

05/03/09 4,696,795.9 232.3 1,840.0 227.2 19 60.00 0.258 0.001

0.2

05/03/09 4,760,996.8 238.5 1,840.0 227.7 19 60.00 0.261 0.001

0.3

05/02/09 4,777,975.0 250.1 1,840.0 228.5 19 60.00 0.261 0.001

0.6

05/02/09 5,040,335.8 268.5 1,840.0 232.8 21 60.00 0.405 0.002

0.5

05/02/09 9,416,853.0 282.6 1,840.0 552.7 51 60.00 0.638 0.006

0.4

05/02/09 9,953,976.7 282.3 1,840.0 605.9 55 60.00 0.513 0.005

05/02/09 9,946,817.1 278.5 1,840.0 600.1 55 60.00 0.414 0.004
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 C

12:00 C

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00 0.8

0.8

05/05/09 9,507,085.1 280.7 1,840.0 552.9 50 60.00 0.858 0.008

0.7

05/05/09 9,502,541.9 282.3 1,840.0 557.8 50 60.00 0.850 0.008

0.7

05/05/09 9,544,514.2 281.9 1,840.0 560.3 50 60.00 0.744 0.007

0.8

05/05/09 9,507,073.1 280.3 1,840.0 558.0 50 60.00 0.744 0.007

0.8

05/05/09 9,494,555.2 281.3 1,840.0 552.2 50 60.00 0.858 0.008

0.6

05/05/09 9,504,680.3 282.7 1,840.0 557.9 50 60.00 0.850 0.008

0.7

05/05/09 9,503,145.9 282.4 1,840.0 557.8 50 60.00 0.638 0.006

0.8

05/05/09 9,482,739.6 280.8 1,840.0 556.6 50 60.00 0.744 0.007

0.7

05/05/09 9,484,529.8 277.8 1,840.0 556.7 50 60.00 0.850 0.008

0.6

05/05/09 9,498,246.8 276.8 1,840.0 557.5 50 60.00 0.744 0.007

0.5

05/05/09 9,444,219.9 277.1 1,840.0 554.3 50 60.00 0.638 0.006

0.4

05/05/09 9,463,904.0 275.8 1,840.0 555.5 50 60.00 0.532 0.005

0.2

05/05/09 9,485,158.5 271.5 1,840.0 556.7 50 60.00 0.425 0.004

0.0

05/05/09 9,355,639.6 261.6 1,840.0 559.3 50 60.00 0.209 0.002

0.0

05/05/09 7,711,034.5 241.4 1,840.0 502.9 45 60.00 0.000 0.000

0.1

05/05/09 5,429,737.7 232.7 1,840.0 301.0 26 60.00 0.000 0.000

0.2

05/05/09 5,341,424.7 230.1 1,840.0 296.1 26 60.00 0.113 0.001

0.2

05/05/09 5,303,817.9 227.8 1,840.0 288.3 25 60.00 0.230 0.001

0.3

05/05/09 4,844,012.6 226.4 1,840.0 242.2 20 60.00 0.250 0.001

0.2

05/05/09 4,843,649.3 230.3 1,840.0 226.4 19 60.00 0.401 0.001

0.2

05/05/09 4,646,218.0 239.3 1,840.0 224.7 19 60.00 0.258 0.001

0.4

05/04/09 4,646,648.6 254.6 1,840.0 227.3 19 60.00 0.255 0.001

0.5

05/04/09 6,366,119.0 273.2 1,840.0 311.4 29 60.00 0.510 0.003

0.4

05/04/09 9,417,876.3 283.6 1,840.0 557.9 51 60.00 0.527 0.005

0.4

05/04/09 10,027,863.7 285.9 1,840.0 605.0 55 60.00 0.414 0.004

0.5

05/04/09 10,029,425.8 286.9 1,840.0 605.0 55 60.00 0.414 0.004

0.7

05/04/09 10,020,977.5 287.0 1,840.0 604.5 55 60.00 0.517 0.005

0.7

05/04/09 9,989,033.6 285.3 1,840.0 608.0 55 60.00 0.718 0.007

0.7

05/04/09 9,961,768.6 285.4 1,840.0 606.4 55 60.00 0.718 0.007

0.7

05/04/09 9,981,743.2 285.4 1,840.0 613.0 55 60.00 0.711 0.007

0.7

05/04/09 10,020,944.2 284.1 1,840.0 610.0 55 60.00 0.718 0.007

0.7

05/04/09 10,066,694.2 283.1 1,840.0 607.3 55 60.00 0.724 0.007

0.7

05/04/09 10,075,579.6 283.8 1,840.0 613.3 55 60.00 0.718 0.007

0.7

05/04/09 10,040,171.7 283.4 1,840.0 616.6 55 60.00 0.711 0.007

0.7

05/04/09 9,993,601.0 282.1 1,840.0 613.8 55 60.00 0.711 0.007

0.5

05/04/09 9,985,646.7 280.3 1,840.0 613.3 55 60.00 0.711 0.007

05/04/09 10,001,896.8 279.1 1,840.0 608.8 55 60.00 0.513 0.005
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00 0.2

0.2

05/07/09 5,501,720.2 243.2 1,840.0 281.1 24 60.00 0.244 0.001

0.3

05/07/09 5,504,344.7 241.3 1,840.0 287.2 24 60.00 0.239 0.001

0.3

05/07/09 5,459,617.3 239.0 1,840.0 284.9 24 60.00 0.359 0.002

0.2

05/07/09 5,406,966.8 237.6 1,840.0 285.0 24 60.00 0.355 0.002

0.2

05/07/09 5,374,518.2 236.6 1,840.0 283.4 24 60.00 0.237 0.001

0.1

05/07/09 5,380,979.2 236.6 1,840.0 280.7 24 60.00 0.239 0.001

0.1

05/07/09 5,387,687.8 238.4 1,840.0 281.1 24 60.00 0.120 0.001

0.1

05/07/09 5,447,063.9 240.7 1,840.0 284.2 24 60.00 0.120 0.001

0.0

05/07/09 5,438,992.2 241.0 1,840.0 283.8 24 60.00 0.120 0.001

0.0

05/07/09 5,467,566.0 241.3 1,840.0 282.3 24 60.00 0.000 0.000

0.0

05/06/09 5,464,530.5 244.7 1,840.0 282.2 24 60.00 0.000 0.000

0.1

05/06/09 5,395,898.5 255.8 1,840.0 278.6 24 60.00 0.000 0.000

0.1

05/06/09 6,111,005.9 275.3 1,840.0 312.2 28 60.00 0.122 0.001

0.1

05/06/09 10,107,321.5 285.9 1,840.0 593.2 54 60.00 0.106 0.001

0.4

05/06/09 10,152,863.9 285.3 1,840.0 595.9 55 60.00 0.106 0.001

0.7

05/06/09 10,071,266.6 283.7 1,840.0 596.6 55 60.00 0.421 0.004

0.6

05/06/09 10,053,105.8 284.6 1,840.0 595.5 55 60.00 0.737 0.007

0.7

05/06/09 10,046,775.3 286.6 1,840.0 595.2 55 60.00 0.632 0.006

0.7

05/06/09 10,031,244.7 286.7 1,840.0 599.7 55 60.00 0.731 0.007

0.7

05/06/09 10,068,986.3 285.4 1,840.0 602.0 55 60.00 0.731 0.007

0.7

05/06/09 10,053,422.4 285.5 1,840.0 601.0 55 60.00 0.731 0.007

0.6

05/06/09 10,039,810.4 285.9 1,840.0 600.2 55 60.00 0.731 0.007

0.5

05/06/09 10,079,895.3 284.6 1,840.0 602.6 55 60.00 0.626 0.006

0.6

05/06/09 10,039,111.9 282.0 1,840.0 594.7 55 60.00 0.527 0.005

0.6

05/06/09 10,006,041.0 278.5 1,840.0 592.7 55 60.00 0.632 0.006

0.4

05/06/09 10,049,394.6 276.7 1,840.0 600.8 55 60.00 0.626 0.006

0.2

05/06/09 10,064,470.3 266.1 1,840.0 607.1 55 60.00 0.414 0.004

0.2

05/06/09 7,505,056.3 239.5 1,840.0 428.3 37 60.00 0.219 0.001

0.2

05/06/09 5,513,038.0 237.2 1,840.0 281.6 24 60.00 0.244 0.001

0.2

05/06/09 5,516,279.5 239.6 1,840.0 281.8 24 60.00 0.244 0.001

0.2

05/06/09 5,549,291.4 242.2 1,840.0 283.5 24 60.00 0.244 0.001

0.3

05/06/09 5,550,147.1 250.2 1,840.0 280.5 24 60.00 0.247 0.001

0.6

05/06/09 5,512,921.0 264.3 1,840.0 275.6 24 60.00 0.374 0.002

0.7

05/06/09 8,637,250.1 279.8 1,840.0 483.5 44 60.00 0.669 0.005

0.7

05/05/09 9,480,491.9 281.5 1,840.0 551.3 50 60.00 0.751 0.007

0.8

05/05/09 9,493,229.2 280.8 1,840.0 552.0 50 60.00 0.751 0.007

05/05/09 9,488,806.0 279.3 1,840.0 557.0 50 60.00 0.850 0.008
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00 0.3

0.5

05/08/09 5,294,016.6 254.4 1,840.0 258.9 22 60.00 0.383 0.002

0.8

05/08/09 5,584,278.7 272.1 1,840.0 267.1 24 60.00 0.652 0.003

0.9

05/08/09 10,004,235.7 284.3 1,840.0 532.8 48 60.00 0.937 0.008

0.9

05/08/09 10,205,252.6 282.7 1,840.0 554.6 50 60.00 1.033 0.009

0.9

05/08/09 10,124,854.3 281.5 1,840.0 550.3 50 60.00 1.033 0.009

0.9

05/08/09 10,210,389.0 280.4 1,840.0 549.3 50 60.00 1.044 0.009

0.8

05/08/09 10,239,230.9 280.4 1,840.0 550.9 50 60.00 1.044 0.009

0.9

05/08/09 10,207,268.8 283.5 1,840.0 549.2 50 60.00 0.928 0.008

0.9

05/08/09 10,287,202.0 285.7 1,840.0 553.5 50 60.00 1.044 0.009

0.9

05/08/09 10,281,261.6 284.9 1,840.0 558.8 50 60.00 1.033 0.009

1.0

05/08/09 10,252,364.5 284.2 1,840.0 557.2 50 60.00 1.033 0.009

0.9

05/08/09 10,157,592.5 285.6 1,840.0 557.6 50 60.00 1.137 0.010

0.9

05/08/09 10,127,870.8 286.1 1,840.0 561.4 50 60.00 1.013 0.009

0.8

05/08/09 10,124,228.0 284.3 1,840.0 555.7 50 60.00 1.023 0.009

0.7

05/08/09 10,139,068.5 280.0 1,840.0 556.5 50 60.00 0.909 0.008

0.3

05/08/09 10,168,895.7 274.3 1,840.0 558.2 50 60.00 0.796 0.007

0.3

05/08/09 9,516,215.9 254.6 1,840.0 548.2 48 60.00 0.325 0.003

0.2

05/08/09 6,023,638.7 241.2 1,840.0 301.2 26 60.00 0.374 0.002

0.3

05/08/09 5,865,782.5 240.5 1,840.0 286.9 24 60.00 0.255 0.001

0.3

05/08/09 5,828,921.3 242.3 1,840.0 285.1 24 60.00 0.383 0.002

0.3

05/08/09 5,851,221.0 245.3 1,840.0 286.2 24 60.00 0.383 0.002

0.2

05/08/09 5,835,741.8 247.3 1,840.0 285.5 24 60.00 0.383 0.002

0.3

05/08/09 5,874,288.1 252.5 1,840.0 290.5 24 60.00 0.252 0.001

0.2

05/07/09 5,855,966.3 264.3 1,840.0 283.3 24 60.00 0.387 0.002

0.3

05/07/09 7,782,092.3 278.3 1,840.0 461.0 42 60.00 0.211 0.002

0.6

05/07/09 8,778,410.4 282.7 1,840.0 548.6 50 60.00 0.300 0.003

0.6

05/07/09 9,591,535.9 283.4 1,840.0 552.6 50 60.00 0.650 0.006

0.5

05/07/09 9,596,966.9 280.4 1,840.0 558.1 50 60.00 0.644 0.006

0.4

05/07/09 9,593,055.5 278.0 1,840.0 552.6 50 60.00 0.542 0.005

0.1

05/07/09 9,624,531.7 271.3 1,840.0 559.7 50 60.00 0.429 0.004

0.3

05/07/09 7,761,783.8 248.7 1,840.0 442.9 38 60.00 0.109 0.001

0.5

05/07/09 5,491,953.7 242.7 1,840.0 286.5 24 60.00 0.359 0.002

0.6

05/07/09 5,412,553.8 241.3 1,840.0 282.4 24 60.00 0.598 0.003

0.5

05/07/09 5,435,870.1 241.0 1,840.0 283.6 24 60.00 0.718 0.003

0.4

05/07/09 5,408,469.7 240.7 1,840.0 285.1 24 60.00 0.592 0.003

0.3

05/07/09 5,432,200.1 242.9 1,840.0 283.4 24 60.00 0.478 0.002

05/07/09 5,481,895.9 244.0 1,840.0 283.0 24 60.00 0.363 0.002
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 0.9

0.5

05/10/09 5,394,986.8 230.3 1,840.0 266.8 22 60.00 1.136 0.005

0.6

05/10/09 5,400,058.5 232.7 1,840.0 267.1 22 60.00 0.631 0.003

0.6

05/10/09 5,439,277.9 233.0 1,840.0 266.0 22 60.00 0.765 0.003

0.5

05/10/09 5,479,231.6 232.5 1,840.0 268.0 22 60.00 0.765 0.003

1.1

05/10/09 5,476,444.8 231.1 1,840.0 267.8 22 60.00 0.638 0.003

1.1

05/10/09 5,409,994.6 229.9 1,840.0 267.6 22 60.00 1.388 0.006

0.7

05/10/09 5,513,660.1 229.9 1,840.0 263.7 22 60.00 1.435 0.006

0.8

05/10/09 5,592,808.3 231.6 1,840.0 264.5 22 60.00 0.924 0.004

0.7

05/10/09 5,637,156.1 232.6 1,840.0 266.5 22 60.00 1.056 0.004

0.5

05/10/09 5,643,449.1 232.5 1,840.0 257.6 22 60.00 0.957 0.004

0.5

05/10/09 5,750,341.8 233.3 1,840.0 268.8 22 60.00 0.668 0.003

0.7

05/10/09 5,615,490.7 235.7 1,840.0 265.5 22 60.00 0.660 0.003

0.7

05/09/09 5,608,783.8 238.8 1,840.0 265.2 22 60.00 0.924 0.004

0.6

05/09/09 5,623,569.2 244.4 1,840.0 265.9 22 60.00 0.924 0.004

0.9

05/09/09 5,624,225.0 257.1 1,840.0 262.9 22 60.00 0.801 0.003

1.1

05/09/09 7,837,685.3 274.5 1,840.0 383.4 35 60.00 1.148 0.007

1.0

05/09/09 9,847,132.3 279.3 1,840.0 561.9 50 60.00 1.203 0.011

0.9

05/09/09 9,884,043.8 278.8 1,840.0 558.7 50 60.00 1.104 0.010

0.9

05/09/09 9,853,155.9 277.6 1,840.0 556.9 50 60.00 0.994 0.009

1.0

05/09/09 9,828,624.8 278.8 1,840.0 560.9 50 60.00 0.984 0.009

0.9

05/09/09 9,847,455.6 279.4 1,840.0 561.9 50 60.00 1.093 0.010

0.9

05/09/09 9,731,671.9 279.3 1,840.0 565.9 50 60.00 0.966 0.009

1.1

05/09/09 9,793,571.1 278.6 1,840.0 558.9 50 60.00 0.984 0.009

1.0

05/09/09 9,777,083.2 280.0 1,840.0 557.9 50 60.00 1.203 0.011

1.0

05/09/09 9,701,076.2 279.9 1,840.0 558.9 50 60.00 1.083 0.010

1.1

05/09/09 9,656,786.6 278.8 1,840.0 561.6 50 60.00 1.073 0.010

1.0

05/09/09 9,695,933.8 276.2 1,840.0 558.6 50 60.00 1.191 0.011

0.8

05/09/09 9,740,770.3 270.7 1,840.0 561.2 50 60.00 1.083 0.010

0.3

05/09/09 9,851,489.7 262.0 1,840.0 556.8 50 60.00 0.883 0.008

0.3

05/09/09 8,901,708.4 239.4 1,840.0 488.6 43 60.00 0.341 0.003

0.1

05/09/09 5,443,248.6 228.5 1,840.0 263.3 22 60.00 0.387 0.002

0.2

05/09/09 5,433,004.9 228.0 1,840.0 262.8 23 60.00 0.129 0.001

0.2

05/09/09 5,366,453.2 227.8 1,840.0 262.5 23 60.00 0.255 0.001

0.2

05/09/09 5,373,107.9 229.1 1,840.0 262.8 23 60.00 0.255 0.001

0.2

05/09/09 5,302,012.2 230.7 1,840.0 259.3 22 60.00 0.255 0.001

0.2

05/09/09 5,286,573.1 235.6 1,840.0 252.9 21 60.00 0.261 0.001

05/08/09 5,278,456.2 243.7 1,840.0 261.0 22 60.00 0.252 0.001
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00 2.3

2.1

05/12/09 5,415,455.0 247.2 1,840.0 270.8 22 60.00 2.870 0.012

2.2

05/11/09 5,493,804.8 258.6 1,840.0 268.7 22 60.00 2.679 0.012

2.8

05/11/09 6,848,620.3 276.1 1,840.0 331.3 29 60.00 2.838 0.015

2.0

05/11/09 10,149,775.0 281.9 1,840.0 562.7 50 60.00 3.152 0.028

2.0

05/11/09 10,178,274.3 284.1 1,840.0 558.7 50 60.00 2.274 0.020

2.0

05/11/09 10,054,558.4 285.5 1,840.0 562.9 50 60.00 2.229 0.020

2.2

05/11/09 10,053,227.1 286.0 1,840.0 562.7 50 60.00 2.229 0.020

2.4

05/11/09 10,089,656.7 284.7 1,840.0 564.8 50 60.00 2.452 0.022

2.6

05/11/09 10,089,406.6 282.1 1,840.0 564.8 50 60.00 2.675 0.024

2.1

05/11/09 10,098,208.1 280.8 1,840.0 565.3 50 60.00 2.898 0.026

1.7

05/11/09 10,084,885.1 282.2 1,840.0 559.1 50 60.00 2.364 0.021

1.4

05/11/09 10,072,949.6 282.4 1,840.0 563.9 50 60.00 1.895 0.017

1.3

05/11/09 10,021,617.1 281.2 1,840.0 566.5 50 60.00 1.546 0.014

1.3

05/11/09 10,027,582.1 279.4 1,840.0 566.8 50 60.00 1.435 0.013

1.3

05/11/09 9,993,700.6 279.9 1,840.0 564.9 50 60.00 1.435 0.013

1.3

05/11/09 9,959,198.9 279.9 1,840.0 562.9 50 60.00 1.435 0.013

1.2

05/11/09 9,955,035.6 277.9 1,840.0 568.1 50 60.00 1.422 0.013

0.9

05/11/09 9,920,672.2 273.7 1,840.0 560.8 50 60.00 1.325 0.012

0.5

05/11/09 9,960,898.6 266.3 1,840.0 563.0 50 60.00 0.994 0.009

0.2

05/11/09 8,953,581.0 245.3 1,840.0 491.5 42 60.00 0.568 0.004

0.4

05/11/09 5,855,221.0 234.4 1,840.0 292.8 24 60.00 0.250 0.001

0.4

05/11/09 5,569,376.5 231.6 1,840.0 284.5 24 60.00 0.489 0.002

0.7

05/11/09 5,510,047.0 230.3 1,840.0 278.5 24 60.00 0.494 0.002

0.6

05/11/09 6,257,804.8 232.4 1,840.0 268.7 24 60.00 1.017 0.004

0.5

05/11/09 6,587,197.3 231.6 1,840.0 268.5 23 60.00 0.919 0.004

0.6

05/10/09 5,951,441.9 229.0 1,840.0 268.4 23 60.00 0.692 0.003

0.7

05/10/09 5,931,184.5 227.2 1,840.0 264.3 23 60.00 0.840 0.004

0.5

05/10/09 5,710,008.7 227.0 1,840.0 251.4 22 60.00 0.992 0.004

0.3

05/10/09 5,826,366.3 228.9 1,840.0 253.3 22 60.00 0.718 0.003

0.3

05/10/09 5,714,622.4 229.1 1,840.0 254.7 22 60.00 0.420 0.002

0.6

05/10/09 5,464,031.8 229.5 1,840.0 255.4 22 60.00 0.401 0.002

0.8

05/10/09 5,450,324.6 229.4 1,840.0 260.7 22 60.00 0.783 0.003

0.7

05/10/09 5,381,330.2 230.0 1,840.0 266.1 22 60.00 1.009 0.004

0.7

05/10/09 5,426,677.6 231.9 1,840.0 265.5 22 60.00 0.893 0.004

0.7

05/10/09 5,473,967.4 231.7 1,840.0 267.8 22 60.00 0.893 0.004

0.7

05/10/09 5,483,985.6 230.8 1,840.0 271.2 22 60.00 0.883 0.004

05/10/09 5,491,548.9 229.5 1,840.0 268.6 22 60.00 0.893 0.004
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 C

12:00 C

13:00

14:00

15:00 C

16:00 S S SC

17:00 C

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00 1.4

1.5

05/13/09 5,459,941.9 242.6 1,840.0 264.1 23 60.00 1.806 0.008

1.7

05/13/09 5,454,051.2 253.0 1,840.0 260.8 22 60.00 1.957 0.008

2.1

05/13/09 6,443,597.2 269.9 1,840.0 304.7 28 60.00 2.244 0.011

2.4

05/13/09 9,585,826.6 273.8 1,840.0 552.2 49 60.00 2.275 0.020

2.3

05/13/09 8,966,625.1 272.3 1,840.0 502.0 45 60.00 2.675 0.021

2.0

05/13/09 9,825,793.4 272.9 1,840.0 560.7 50 60.00 2.515 0.023

1.6

05/13/09 9,746,329.3 267.6 1,840.0 556.2 50 60.00 2.187 0.019

1.1

05/13/09 9,397,195.2 246.2 1,840.0 536.2 46 60.00 1.750 0.015

1.2

05/13/09 6,107,359.1 232.7 1,840.0 295.4 25 60.00 1.419 0.007

1.3

05/13/09 5,463,675.2 233.4 1,840.0 270.2 23 60.00 1.514 0.007

1.3

05/13/09 5,462,594.0 233.6 1,840.0 273.2 23 60.00 1.622 0.007

1.4

05/13/09 5,377,425.6 232.6 1,840.0 265.9 23 60.00 1.640 0.007

2.3

05/13/09 5,398,215.5 231.9 1,840.0 267.0 23 60.00 1.766 0.008

1.9

05/13/09 5,323,030.1 231.7 1,840.0 269.0 23 60.00 2.840 0.012

1.6

05/12/09 5,392,017.5 233.1 1,840.0 269.6 23 60.00 2.371 0.010

1.3

05/12/09 5,520,229.7 234.7 1,840.0 270.0 22 60.00 2.041 0.009

1.5

05/12/09 5,400,196.6 234.8 1,840.0 264.1 22 60.00 1.658 0.007

1.4

05/12/09 5,543,572.0 234.7 1,840.0 271.2 22 60.00 1.914 0.008

1.3

05/12/09 5,442,877.1 234.3 1,840.0 269.2 22 60.00 1.766 0.008

1.5

05/12/09 5,373,147.5 235.6 1,840.0 268.6 22 60.00 1.622 0.007

1.3

05/12/09 5,424,484.9 236.2 1,840.0 268.3 22 60.00 1.893 0.008

1.2

05/12/09 5,445,923.6 236.2 1,840.0 272.3 22 60.00 1.622 0.007

1.5

05/12/09 5,456,021.7 237.3 1,840.0 269.8 22 60.00 1.514 0.007

1.5

05/12/09 5,427,414.0 240.3 1,840.0 268.4 22 60.00 1.893 0.008

1.4

05/12/09 5,454,353.0 242.2 1,840.0 272.7 22 60.00 1.872 0.008

1.2

05/12/09 5,456,189.3 245.2 1,840.0 269.8 22 60.00 1.766 0.008

1.9

05/12/09 5,458,744.8 251.8 1,840.0 267.0 22 60.00 1.531 0.007

2.2

05/12/09 5,783,789.6 266.6 1,840.0 264.1 22 60.00 2.597 0.011

2.3

05/12/09 9,063,372.8 281.4 1,840.0 487.6 43 60.00 2.551 0.020

2.3

05/12/09 9,996,092.8 283.5 1,840.0 565.0 50 60.00 2.539 0.023

2.3

05/12/09 9,855,784.6 282.1 1,840.0 567.8 50 60.00 2.491 0.023

1.5

05/12/09 10,213,257.9 274.4 1,840.0 566.2 50 60.00 2.589 0.023

2.6

05/12/09 8,864,509.3 248.5 1,840.0 491.4 42 60.00 1.688 0.013

2.6

05/12/09 5,435,400.5 239.1 1,840.0 271.8 22 60.00 3.245 0.014

2.5

05/12/09 5,380,834.6 239.3 1,840.0 269.1 22 60.00 3.245 0.014

2.2

05/12/09 5,381,867.2 240.5 1,840.0 266.2 22 60.00 3.154 0.013

05/12/09 5,398,087.5 242.2 1,840.0 269.9 22 60.00 2.746 0.012
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S 0.9 S

1.4

05/15/09 5,572,158.3 232.0 1,840.0 263.5 22 60.00 1.188 0.005

1.3

05/15/09 5,566,970.7 233.1 1,840.0 260.2 22 60.00 1.869 0.008

1.0

05/15/09 5,558,483.9 235.8 1,840.0 259.8 22 60.00 1.736 0.007

0.8

05/14/09 5,506,077.4 242.8 1,840.0 257.3 22 60.00 1.335 0.005

1.1

05/14/09 5,465,637.3 257.7 1,840.0 255.5 22 60.00 1.068 0.004

1.1

05/14/09 7,137,010.4 277.1 1,840.0 353.0 33 60.00 1.388 0.008

0.9

05/14/09 10,350,699.8 283.8 1,840.0 613.2 55 60.00 1.159 0.011

1.0

05/14/09 9,735,340.9 283.3 1,840.0 555.5 50 60.00 0.984 0.009

1.0

05/14/09 9,571,649.8 281.4 1,840.0 561.8 50 60.00 1.063 0.010

0.9

05/14/09 9,759,176.6 282.2 1,840.0 551.6 50 60.00 1.104 0.010

1.0

05/14/09 9,780,417.8 281.7 1,840.0 558.1 50 60.00 0.984 0.009

0.7

05/14/09 9,715,744.7 276.6 1,840.0 559.7 50 60.00 1.083 0.010

0.8

05/14/09 8,576,818.4 265.8 1,840.0 470.8 41 60.00 0.796 0.006

1.1

05/14/09 6,826,807.8 277.1 1,840.0 348.8 32 60.00 0.977 0.005

1.1

05/14/09 9,690,957.3 285.2 1,840.0 547.8 49 60.00 1.214 0.011

1.1

05/14/09 9,704,190.6 285.1 1,840.0 553.8 50 60.00 1.203 0.011

1.2

05/14/09 9,600,355.9 283.1 1,840.0 558.3 50 60.00 1.180 0.011

1.3

05/14/09 9,603,540.8 280.3 1,840.0 553.3 50 60.00 1.300 0.011

1.5

05/14/09 9,583,783.2 275.2 1,840.0 557.3 50 60.00 1.395 0.012

1.3

05/14/09 9,368,958.8 262.3 1,840.0 549.9 50 60.00 1.595 0.014

1.7

05/14/09 8,575,302.2 238.2 1,840.0 503.3 46 60.00 1.382 0.011

1.1

05/14/09 5,302,777.8 228.0 1,840.0 245.0 22 60.00 2.296 0.009

1.2

05/14/09 5,308,318.8 230.6 1,840.0 242.3 22 60.00 1.504 0.006

1.0

05/14/09 5,333,654.1 231.7 1,840.0 243.5 22 60.00 1.640 0.006

1.0

05/14/09 5,308,155.9 232.5 1,840.0 239.4 21 60.00 1.383 0.005

1.1

05/14/09 5,291,734.6 233.7 1,840.0 244.5 21 60.00 1.351 0.005

0.9

05/14/09 5,308,618.3 238.2 1,840.0 242.4 21 60.00 1.504 0.006

0.8

05/13/09 5,294,118.6 245.8 1,840.0 241.7 21 60.00 1.230 0.005

1.4

05/13/09 5,600,175.4 260.0 1,840.0 249.6 21 60.00 1.120 0.004

2.3

05/13/09 7,695,323.1 278.7 1,840.0 380.6 36 60.00 1.766 0.011

2.4

05/13/09 9,991,397.9 281.1 1,840.0 559.3 51 60.00 2.564 0.023

2.4

05/13/09 9,959,199.2 279.4 1,840.0 557.5 51 60.00 2.675 0.024

2.3

05/13/09 9,812,697.7 279.9 1,840.0 560.0 51 60.00 2.624 0.023

2.3

05/13/09 9,744,598.5 279.2 1,840.0 566.7 51 60.00 2.468 0.022

2.2

05/13/09 9,664,230.1 274.9 1,840.0 562.0 50 60.00 2.468 0.022

1.4

05/13/09 9,717,103.8 262.8 1,840.0 559.8 50 60.00 2.383 0.021

05/13/09 7,305,263.6 240.3 1,840.0 397.0 35 60.00 1.607 0.010
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00 C

14:00 S S SC

15:00 S S SC

16:00 C

17:00

18:00 S S S

19:00 S S S

20:00

21:00 C

22:00 S S SC

23:00 C

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00 1.3

1.6

05/16/09 5,718,678.9 237.1 1,840.0 279.7 24 60.00 1.658 0.007

1.6

05/16/09 5,504,189.6 238.9 1,840.0 272.2 24 60.00 2.019 0.009

1.3

05/16/09 5,541,152.0 247.5 1,840.0 274.0 24 60.00 2.019 0.009

1.2

05/16/09 5,818,106.8 263.2 1,840.0 275.1 24 60.00 1.716 0.008

1.9

05/16/09 8,823,506.3 273.5 1,840.0 513.1 47 60.00 1.288 0.011

1.8

05/16/09 9,306,468.7 271.7 1,840.0 546.2 50 60.00 2.020 0.018

1.8

05/16/09 9,116,313.6 265.4 1,840.0 525.2 47 60.00 1.950 0.016

1.1

05/16/09 8,982,445.8 258.6 1,840.0 493.0 45 60.00 2.046 0.016

1.0

05/16/09 8,604,254.8 243.2 1,840.0 467.6 41 60.00 1.263 0.009

1.0

05/16/09 5,569,181.2 236.4 1,840.0 272.4 24 60.00 1.276 0.006

1.0

05/16/09 5,683,284.7 236.0 1,840.0 278.0 24 60.00 1.276 0.006

1.5

05/16/09 5,586,098.2 235.2 1,840.0 276.3 24 60.00 1.262 0.006

1.1

05/16/09 5,639,611.4 235.2 1,840.0 272.8 24 60.00 1.935 0.008

1.1

05/16/09 5,676,106.5 236.6 1,840.0 271.5 24 60.00 1.435 0.006

1.1

05/16/09 5,607,169.4 236.7 1,840.0 277.3 24 60.00 1.388 0.006

0.8

05/16/09 5,466,840.4 236.8 1,840.0 273.3 24 60.00 1.373 0.006

0.9

05/15/09 5,500,404.5 239.6 1,840.0 269.0 23 60.00 1.021 0.004

1.1

05/15/09 5,447,657.6 247.4 1,840.0 269.4 23 60.00 1.136 0.005

1.3

05/15/09 5,756,805.9 262.2 1,840.0 262.8 23 60.00 1.504 0.006

1.3

05/15/09 8,740,238.3 274.0 1,840.0 489.3 46 60.00 1.449 0.011

1.3

05/15/09 9,262,131.1 273.8 1,840.0 538.6 50 60.00 1.395 0.012

1.3

05/15/09 9,271,130.6 272.5 1,840.0 544.2 50 60.00 1.382 0.012

1.2

05/15/09 9,380,187.1 274.0 1,840.0 545.5 50 60.00 1.395 0.012

1.4

05/15/09 9,284,495.0 274.5 1,840.0 544.9 50 60.00 1.276 0.011

1.4

05/15/09 9,307,277.3 274.2 1,840.0 546.3 50 60.00 1.488 0.013

1.7

05/15/09 9,323,253.4 273.3 1,840.0 552.3 50 60.00 1.475 0.013

0.8

05/15/09 9,372,034.9 272.2 1,840.0 555.2 50 60.00 1.791 0.016

0.8

05/15/09 9,262,767.0 265.6 1,840.0 553.8 49 60.00 0.835 0.007

0.7

05/15/09 8,196,487.7 254.2 1,840.0 467.7 42 60.00 0.875 0.007

0.9

05/15/09 7,921,448.8 237.6 1,840.0 443.4 40 60.00 0.780 0.006

0.8

05/15/09 5,686,915.5 231.7 1,840.0 259.6 22 60.00 1.230 0.005

0.6

05/15/09 5,599,047.6 231.2 1,840.0 258.6 22 60.00 1.081 0.004

0.4

05/15/09 5,549,043.8 230.6 1,840.0 259.4 22 60.00 0.801 0.003

0.5

05/15/09 5,466,644.5 230.8 1,840.0 258.5 22 60.00 0.528 0.002

0.4

05/15/09 5,354,680.9 231.9 1,840.0 261.9 22 60.00 0.638 0.003

0.9

05/15/09 5,329,242.7 231.7 1,840.0 260.7 22 60.00 0.510 0.002

05/15/09 5,339,631.2 231.5 1,840.0 258.3 22 60.00 1.161 0.005
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 1.3 C

1.2

05/18/09 5,427,938.5 235.2 1,840.0 283.2 24 60.00 1.555 0.007

1.6

05/18/09 5,439,561.3 235.1 1,840.0 280.9 23 60.00 1.450 0.007

1.3

05/18/09 5,341,062.2 236.9 1,840.0 281.6 24 60.00 1.894 0.009

1.0

05/18/09 5,376,351.4 242.0 1,840.0 277.6 23 60.00 1.571 0.007

1.2

05/18/09 5,500,199.0 251.0 1,840.0 278.0 23 60.00 1.235 0.005

1.5

05/17/09 6,479,210.5 264.3 1,840.0 313.4 29 60.00 1.548 0.008

1.3

05/17/09 9,478,158.8 272.0 1,840.0 525.4 49 60.00 1.688 0.014

1.4

05/17/09 9,519,927.0 272.3 1,840.0 527.7 49 60.00 1.463 0.012

1.3

05/17/09 9,435,309.8 272.5 1,840.0 528.2 49 60.00 1.561 0.013

1.5

05/17/09 9,559,099.4 273.5 1,840.0 535.1 50 60.00 1.449 0.012

1.6

05/17/09 9,138,015.9 269.8 1,840.0 521.5 46 60.00 1.640 0.014

1.3

05/17/09 9,190,063.3 262.3 1,840.0 529.4 47 60.00 1.733 0.015

1.5

05/17/09 7,563,787.1 241.1 1,840.0 419.3 37 60.00 1.463 0.010

1.4

05/17/09 5,524,512.4 237.7 1,840.0 279.3 24 60.00 1.852 0.008

1.3

05/17/09 5,547,224.6 236.9 1,840.0 280.4 24 60.00 1.728 0.008

2.0

05/17/09 5,527,115.1 235.6 1,840.0 279.4 24 60.00 1.605 0.007

2.0

05/17/09 5,511,118.0 235.5 1,840.0 278.5 24 60.00 2.469 0.011

1.8

05/17/09 5,520,380.2 236.1 1,840.0 276.0 24 60.00 2.496 0.011

1.4

05/17/09 5,518,926.2 237.3 1,840.0 275.9 24 60.00 2.246 0.010

1.6

05/17/09 5,554,650.5 238.3 1,840.0 277.8 24 60.00 1.747 0.008

1.5

05/17/09 5,591,605.0 237.3 1,840.0 279.6 24 60.00 1.997 0.009

1.5

05/17/09 5,564,024.3 235.2 1,840.0 278.2 24 60.00 1.872 0.008

1.9

05/17/09 5,588,916.9 232.8 1,840.0 279.4 24 60.00 1.872 0.008

1.9

05/17/09 5,489,967.7 231.5 1,840.0 277.5 24 60.00 2.346 0.010

1.6

05/17/09 5,482,008.8 231.3 1,840.0 277.1 24 60.00 2.346 0.010

1.6

05/17/09 5,477,543.5 232.0 1,840.0 276.9 24 60.00 1.975 0.009

1.3

05/17/09 5,581,087.2 233.9 1,840.0 276.0 24 60.00 2.019 0.009

1.3

05/17/09 5,561,703.7 233.6 1,840.0 278.1 24 60.00 1.622 0.007

1.3

05/17/09 5,574,916.3 232.8 1,840.0 275.7 24 60.00 1.640 0.007

1.6

05/16/09 5,555,199.3 232.2 1,840.0 274.7 24 60.00 1.640 0.007

1.4

05/16/09 5,511,218.5 233.4 1,840.0 275.6 24 60.00 1.997 0.009

1.5

05/16/09 5,564,402.6 234.7 1,840.0 275.2 24 60.00 1.766 0.008

1.4

05/16/09 5,559,150.0 234.7 1,840.0 274.9 24 60.00 1.893 0.008

1.3

05/16/09 5,570,082.0 234.6 1,840.0 275.5 24 60.00 1.766 0.008

1.2

05/16/09 5,511,774.0 235.4 1,840.0 275.6 24 60.00 1.622 0.007

1.2

05/16/09 5,565,878.4 236.8 1,840.0 275.3 24 60.00 1.514 0.007

05/16/09 5,610,077.6 237.1 1,840.0 277.5 24 60.00 1.514 0.007
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

05:00 C C

06:00

07:00 S S S

08:00 S S S

09:00 S S S

10:00 S S S

11:00 M

12:00 S S S

13:00 S S S

14:00

15:00

16:00 S S S

17:00

18:00

19:00

20:00 S S S

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 S S S

05:00 C S S SC

06:00 S S S

07:00 S S S

08:00 S S S

09:00 S S S

10:00 C

11:00 S S SC

12:00 S S SC

13:00 S S SC

14:00 S S SC

15:00 S S S

16:00

17:00 0.9

1.0

05/19/09 9,236,591.6 276.8 1,840.0 562.3 50 60.00 0.923 0.008

1.1

05/19/09 9,521,588.0 276.2 1,840.0 558.9 50 60.00 1.063 0.010

1.1

05/19/09 9,455,350.9 274.8 1,840.0 544.7 50 60.00 1.191 0.010

1.1

05/19/09 9,559,597.3 274.8 1,840.0 550.7 50 60.00 1.191 0.010

1.1

05/19/09 9,532,640.6 277.7 1,840.0 549.2 50 60.00 1.191 0.010

1.1

05/19/09 9,542,107.4 278.9 1,840.0 549.7 50 60.00 1.191 0.010

1.1

05/19/09 9,471,861.7 278.5 1,840.0 550.8 50 60.00 1.180 0.010

0.7

05/19/09 9,472,954.5 278.3 1,840.0 550.9 50 60.00 1.180 0.010

0.7

05/19/09 9,377,168.3 277.6 1,840.0 550.4 49 60.00 0.744 0.007

0.7

05/19/09 9,431,555.0 274.6 1,840.0 553.6 49 60.00 0.744 0.007

0.7

05/19/09 9,331,626.7 270.1 1,840.0 552.8 49 60.00 0.737 0.007

0.7

05/19/09 9,443,351.3 259.0 1,840.0 559.4 50 60.00 0.737 0.007

0.7

05/19/09 6,954,668.4 238.2 1,840.0 381.8 33 60.00 0.796 0.005

0.7

05/19/09 5,329,520.8 236.6 1,840.0 278.1 24 60.00 0.837 0.004

0.7

05/19/09 5,395,900.9 238.2 1,840.0 281.5 24 60.00 0.837 0.004

0.4

05/19/09 5,585,550.5 240.9 1,840.0 288.4 24 60.00 0.846 0.004

0.4

05/19/09 5,603,473.0 242.4 1,840.0 292.3 24 60.00 0.478 0.002

0.5

05/19/09 5,588,723.2 244.5 1,840.0 291.6 24 60.00 0.478 0.002

0.9

05/18/09 5,594,664.4 249.7 1,840.0 291.9 24 60.00 0.598 0.003

0.9

05/18/09 5,783,943.0 262.0 1,840.0 292.3 24 60.00 1.111 0.005

0.8

05/18/09 8,448,695.3 275.2 1,840.0 463.8 41 60.00 1.023 0.008

0.7

05/18/09 9,773,668.8 278.9 1,840.0 579.0 49 60.00 0.843 0.008

0.7

05/18/09 9,819,663.3 281.7 1,840.0 576.4 49 60.00 0.744 0.007

0.8

05/18/09 9,689,396.4 280.2 1,840.0 563.4 50 60.00 0.751 0.007

0.8

05/18/09 9,698,067.8 277.3 1,840.0 569.2 50 60.00 0.850 0.008

0.8

05/18/09 9,617,358.8 276.1 1,840.0 564.5 50 60.00 0.850 0.008

9.6

05/18/09 9,421,193.3 277.3 1,840.0 568.3 50 60.00 0.828 0.008

35.5

05/18/09 9,448,199.7 277.3 1,840.0 570.0 50 60.00 9.930 0.091

35.5

05/18/09 9,385,808.7 277.3 1,840.0 561.1 50 60.00 37.054 0.332

61.3

05/18/09 9,374,243.2 277.5 1,840.0 560.4 50 60.00 37.054 0.332

31.4

05/18/09 9,426,912.1 279.9 1,840.0 563.6 50 60.00 63.984 0.577

31.4

05/18/09 9,561,383.3 280.9 1,840.0 566.4 50 60.00 33.075 0.300

31.4

05/18/09 9,582,433.6 279.8 1,840.0 557.2 50 60.00 33.694 0.300

31.4

05/18/09 9,548,652.0 275.8 1,840.0 565.7 50 60.00 33.075 0.299

1.5

05/18/09 9,256,892.7 268.5 1,840.0 553.4 50 60.00 32.775 0.290

0.9

05/18/09 9,801,213.9 260.1 1,840.0 569.9 51 60.00 1.610 0.015

05/18/09 6,847,888.3 237.7 1,840.0 379.6 32 60.00 1.013 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

18:00

19:00

20:00

21:00

22:00 C

23:00 S S SC

00:00

01:00 C

02:00 C C

03:00 S S S

04:00 S S SC

05:00 C C

06:00 S S S

07:00 S S S

08:00 S S S

09:00 * *

10:00 S S

11:00 S S

12:00 S S

13:00 S S

14:00

15:00 C

16:00 C

17:00

18:00 C

19:00 C

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00 0.0

0.0

05/21/09 5,209,241.7 235.6 1,840.0 283.1 24 60.00 0.000 0.000

0.0

05/21/09 5,276,516.2 235.4 1,840.0 283.9 24 60.00 0.000 0.000

0.0

05/21/09 5,258,148.8 236.6 1,840.0 285.8 24 60.00 0.000 0.000

0.0

05/21/09 5,283,025.3 237.6 1,840.0 284.2 24 60.00 0.000 0.000

0.0

05/21/09 5,357,278.5 237.3 1,840.0 282.4 24 60.00 0.000 0.000

0.0

05/21/09 5,431,703.2 239.9 1,840.0 274.6 24 60.00 0.000 0.000

0.2

05/21/09 5,146,559.9 250.0 1,840.0 262.9 24 60.00 0.000 0.000

0.6

05/20/09 5,480,244.8 265.5 1,840.0 274.0 26 60.00 0.250 0.001

0.5

05/20/09 8,928,550.3 273.3 1,840.0 514.4 47 60.00 0.650 0.005

0.6

05/20/09 8,885,472.3 273.4 1,840.0 516.7 48 60.00 0.537 0.004

0.7

05/20/09 8,896,604.7 274.2 1,840.0 536.7 48 60.00 0.621 0.005

0.6

05/20/09 8,973,058.1 275.8 1,840.0 541.3 48 60.00 0.724 0.006

0.6

05/20/09 8,969,640.4 277.3 1,840.0 541.1 48 60.00 0.621 0.005

0.9

05/20/09 9,323,477.8 278.3 1,840.0 567.5 50 60.00 0.615 0.006

0.8

05/20/09 9,339,994.3 278.3 1,840.0 568.5 50 60.00 0.923 0.008

0.7

05/20/09 9,325,898.7 280.5 1,840.0 567.7 50 60.00 0.820 0.007

0.6

05/20/09 9,298,218.7 280.7 1,840.0 571.0 50 60.00 0.711 0.006

0.8

05/20/09 9,301,419.7 281.1 1,840.0 566.1 50 60.00 0.615 0.006

0.9

05/20/09 9,331,905.6 280.2 1,840.0 568.0 50 60.00 0.820 0.007

0.9

05/20/09 9,305,354.6 278.7 1,840.0 566.4 50 60.00 0.923 0.008

1.0

05/20/09 9,348,530.7 276.7 1,840.0 569.1 50 60.00 0.923 0.008

1.5

05/20/09 9,284,655.2 275.9 1,840.0 560.1 50 60.00 1.034 0.009

1.5

05/20/09 9,421,075.2 273.4 1,840.0 563.2 50 60.00 1.566 0.014

1.5

05/20/09 9,544,201.2 260.0 1,840.0 570.6 50 60.00 1.566 0.014

2.0

05/20/09 6,812,549.6 238.1 1,840.0 385.1 33 60.00 1.656 0.010

1.6

05/20/09 5,456,709.9 235.5 1,840.0 281.7 24 60.00 2.417 0.011

1.6

05/20/09 5,726,079.0 236.7 1,840.0 283.2 24 60.00 2.019 0.009

1.3

05/20/09 5,709,771.4 236.5 1,840.0 285.5 24 60.00 1.997 0.009

0.7

05/20/09 5,681,637.8 235.8 1,840.0 284.1 24 60.00 1.622 0.007

1.0

05/20/09 5,575,889.7 236.3 1,840.0 278.8 24 60.00 0.874 0.004

0.7

05/20/09 5,524,256.6 238.4 1,840.0 282.2 24 60.00 1.221 0.006

0.3

05/19/09 5,623,085.7 240.1 1,840.0 284.2 24 60.00 0.864 0.004

0.4

05/19/09 5,451,196.5 242.4 1,840.0 284.4 24 60.00 0.359 0.002

0.5

05/19/09 5,443,812.1 249.3 1,840.0 281.1 24 60.00 0.483 0.002

0.5

05/19/09 6,111,495.0 258.5 1,840.0 322.2 28 60.00 0.592 0.003

0.7

05/19/09 6,354,626.3 268.5 1,840.0 341.9 30 60.00 0.580 0.003

05/19/09 8,696,308.5 276.4 1,840.0 524.6 47 60.00 0.724 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

07:00 C

08:00 C

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00 C

21:00 C

22:00 S S S

23:00 S S S

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00 S S S

07:00 S S S

08:00

09:00

10:00 S S S

11:00 S S S

12:00

13:00

14:00 S S S

15:00 S S S

16:00

17:00

18:00 S S S

19:00 S S 0.4 S

0.4

05/22/09 9,749,050.0 277.6 1,840.0 614.6 55 60.00 0.396 0.004

0.4

05/22/09 9,765,169.6 277.4 1,840.0 620.9 55 60.00 0.393 0.004

0.4

05/22/09 9,815,218.7 273.7 1,840.0 618.8 55 60.00 0.396 0.004

0.6

05/22/09 9,242,331.1 262.1 1,840.0 572.6 50 60.00 0.403 0.004

0.6

05/22/09 6,265,955.5 271.9 1,840.0 323.5 28 60.00 0.725 0.004

0.7

05/22/09 9,845,828.8 285.7 1,840.0 620.7 55 60.00 0.594 0.006

0.6

05/22/09 10,562,462.5 284.8 1,840.0 683.1 60 60.00 0.675 0.007

0.4

05/22/09 10,319,858.4 280.4 1,840.0 667.4 59 60.00 0.579 0.006

0.4

05/22/09 9,982,722.4 278.1 1,840.0 640.2 56 60.00 0.389 0.004

0.2

05/22/09 9,888,485.7 271.5 1,840.0 634.1 56 60.00 0.389 0.004

0.2

05/22/09 9,553,570.3 252.9 1,840.0 602.3 52 60.00 0.198 0.002

0.1

05/22/09 6,161,610.7 238.2 1,840.0 355.0 30 60.00 0.217 0.001

0.1

05/22/09 5,590,519.0 238.5 1,840.0 309.9 27 60.00 0.113 0.001

0.1

05/22/09 5,550,596.8 237.7 1,840.0 313.8 26 60.00 0.110 0.001

0.2

05/22/09 5,581,777.2 237.1 1,840.0 312.5 26 60.00 0.111 0.001

0.1

05/22/09 5,400,516.8 238.7 1,840.0 293.5 24 60.00 0.230 0.001

0.1

05/22/09 5,413,221.7 239.7 1,840.0 291.2 24 60.00 0.116 0.001

0.1

05/22/09 5,401,180.0 242.0 1,840.0 293.5 24 60.00 0.115 0.001

0.2

05/22/09 5,411,326.7 246.9 1,840.0 288.2 24 60.00 0.117 0.001

0.4

05/22/09 5,361,843.0 258.9 1,840.0 285.6 24 60.00 0.234 0.001

0.4

05/21/09 6,112,663.5 274.6 1,840.0 322.3 29 60.00 0.473 0.002

0.7

05/21/09 9,775,309.9 282.4 1,840.0 616.3 55 60.00 0.396 0.004

1.0

05/21/09 9,847,136.0 282.7 1,840.0 626.1 56 60.00 0.687 0.007

1.0

05/21/09 9,860,996.3 284.5 1,840.0 627.0 56 60.00 0.981 0.010

0.9

05/21/09 9,878,721.9 284.4 1,840.0 628.2 56 60.00 0.981 0.010

0.9

05/21/09 9,857,361.3 282.5 1,840.0 626.8 56 60.00 0.883 0.009

0.8

05/21/09 9,898,891.1 279.4 1,840.0 602.5 55 60.00 0.923 0.009

0.7

05/21/09 9,783,881.5 279.6 1,840.0 595.5 55 60.00 0.820 0.008

0.5

05/21/09 9,717,241.2 281.8 1,840.0 596.8 55 60.00 0.711 0.007

0.5

05/21/09 9,840,906.7 281.6 1,840.0 599.0 55 60.00 0.513 0.005

0.2

05/21/09 9,865,941.7 278.1 1,840.0 595.2 55 60.00 0.517 0.005

0.0

05/21/09 9,892,996.9 267.8 1,840.0 586.1 53 60.00 0.211 0.002

0.3

05/21/09 6,015,854.1 266.0 1,840.0 313.9 29 60.00 0.000 0.000

0.2

05/21/09 8,865,556.8 274.9 1,840.0 520.4 49 60.00 0.319 0.003

0.1

05/21/09 9,916,583.5 256.8 1,840.0 630.6 54 60.00 0.196 0.002

0.1

05/21/09 5,739,679.9 236.9 1,840.0 321.3 27 60.00 0.111 0.001

05/21/09 5,264,281.4 236.5 1,840.0 286.1 24 60.00 0.115 0.001
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

20:00

21:00

22:00 S S S

23:00 S S S

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00 S S S

07:00 S S S

08:00

09:00

10:00 S S S

11:00 S S S

12:00

13:00

14:00 S S S

15:00 S S S

16:00

17:00

18:00 S S S

19:00 S S S

20:00

21:00

22:00 S S S

23:00 S S S

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00 S S S

07:00 S S S

08:00 0.8

1.1

05/24/09 10,037,509.2 282.6 1,840.0 638.3 56 60.00 0.785 0.008

1.1

05/24/09 9,925,241.2 279.9 1,840.0 620.3 54 60.00 1.098 0.011

1.5

05/24/09 9,525,140.3 279.9 1,840.0 585.0 51 60.00 1.118 0.010

1.5

05/24/09 9,945,228.1 282.3 1,840.0 627.0 55 60.00 1.485 0.015

1.5

05/24/09 9,855,188.8 282.3 1,840.0 615.9 54 60.00 1.498 0.015

1.5

05/24/09 9,824,333.7 281.5 1,840.0 614.0 54 60.00 1.498 0.015

1.5

05/24/09 9,835,806.7 281.4 1,840.0 614.8 54 60.00 1.498 0.015

1.3

05/24/09 9,856,487.1 283.7 1,840.0 621.4 54 60.00 1.485 0.015

1.2

05/24/09 9,840,822.6 284.8 1,840.0 620.4 54 60.00 1.287 0.013

1.2

05/23/09 9,853,383.8 285.4 1,840.0 615.8 54 60.00 1.198 0.012

1.1

05/23/09 9,899,648.3 284.8 1,840.0 618.8 54 60.00 1.198 0.012

0.9

05/23/09 9,872,175.2 283.4 1,840.0 622.4 54 60.00 1.089 0.011

1.2

05/23/09 9,889,624.6 285.4 1,840.0 618.1 54 60.00 0.899 0.009

1.2

05/23/09 9,858,820.6 286.5 1,840.0 616.2 54 60.00 1.198 0.012

1.6

05/23/09 9,922,216.8 286.4 1,840.0 614.7 54 60.00 1.209 0.012

1.5

05/23/09 9,944,275.2 284.9 1,840.0 621.5 54 60.00 1.597 0.016

1.4

05/23/09 9,912,203.0 282.1 1,840.0 619.5 54 60.00 1.498 0.015

1.4

05/23/09 9,897,461.7 281.0 1,840.0 623.9 55 60.00 1.386 0.014

1.3

05/23/09 9,896,625.5 281.0 1,840.0 618.6 54 60.00 1.398 0.014

0.8

05/23/09 9,831,163.4 279.6 1,840.0 619.8 54 60.00 1.287 0.013

0.5

05/23/09 9,897,163.0 276.0 1,840.0 623.9 55 60.00 0.792 0.008

0.5

05/23/09 9,879,840.5 268.0 1,840.0 622.9 55 60.00 0.495 0.005

0.3

05/23/09 8,612,311.7 245.5 1,840.0 524.2 45 60.00 0.513 0.004

0.3

05/23/09 5,486,760.1 237.2 1,840.0 301.2 25 60.00 0.341 0.002

0.3

05/23/09 5,481,166.7 236.3 1,840.0 300.9 25 60.00 0.341 0.002

0.3

05/23/09 5,411,410.2 235.0 1,840.0 302.9 25 60.00 0.334 0.002

0.4

05/23/09 5,406,924.1 235.9 1,840.0 299.7 25 60.00 0.338 0.002

0.4

05/23/09 5,477,938.4 238.3 1,840.0 300.7 25 60.00 0.455 0.002

0.3

05/23/09 5,511,978.7 239.5 1,840.0 302.6 25 60.00 0.455 0.002

0.3

05/23/09 5,564,019.5 240.8 1,840.0 302.4 25 60.00 0.344 0.002

0.2

05/23/09 5,491,570.1 244.6 1,840.0 298.5 25 60.00 0.344 0.002

0.3

05/23/09 5,462,781.3 253.4 1,840.0 296.9 25 60.00 0.230 0.001

0.4

05/23/09 5,548,645.1 268.8 1,840.0 292.5 25 60.00 0.355 0.002

0.4

05/22/09 8,927,227.5 282.2 1,840.0 538.5 48 60.00 0.414 0.004

0.6

05/22/09 9,919,280.0 281.9 1,840.0 630.7 56 60.00 0.393 0.004

0.5

05/22/09 9,847,195.8 278.6 1,840.0 626.1 55 60.00 0.589 0.006

05/22/09 9,755,425.5 276.4 1,840.0 620.3 55 60.00 0.491 0.005
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

09:00

10:00 S S S

11:00 S S S

12:00

13:00 C

14:00 S S SC

15:00 C

16:00 C

17:00 C

18:00 C

19:00 S S S

20:00 S S S

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00 1.6

1.6

05/25/09 8,437,558.6 282.2 1,840.0 499.9 44 60.00 1.685 0.013

1.5

05/25/09 10,007,578.1 283.9 1,840.0 625.5 55 60.00 1.597 0.016

1.6

05/25/09 9,939,014.2 282.9 1,840.0 615.8 55 60.00 1.511 0.015

1.6

05/25/09 9,932,723.8 283.9 1,840.0 620.8 55 60.00 1.597 0.016

1.6

05/25/09 9,918,479.6 283.4 1,840.0 619.9 55 60.00 1.597 0.016

1.5

05/25/09 9,960,421.0 283.3 1,840.0 622.5 55 60.00 1.597 0.016

1.5

05/25/09 9,904,774.4 282.2 1,840.0 624.4 55 60.00 1.485 0.015

1.4

05/25/09 9,899,428.1 281.8 1,840.0 624.1 55 60.00 1.485 0.015

1.3

05/25/09 9,925,564.4 282.7 1,840.0 625.8 55 60.00 1.386 0.014

1.3

05/25/09 9,976,521.5 279.8 1,840.0 629.0 55 60.00 1.287 0.013

1.2

05/25/09 10,003,400.9 264.7 1,840.0 641.5 55 60.00 1.265 0.013

1.3

05/25/09 6,696,771.5 239.3 1,840.0 389.4 32 60.00 1.288 0.008

1.2

05/25/09 5,490,154.5 236.7 1,840.0 307.3 25 60.00 1.449 0.007

0.9

05/25/09 5,500,578.4 236.4 1,840.0 307.9 25 60.00 1.338 0.007

0.8

05/25/09 5,545,871.7 236.8 1,840.0 307.4 25 60.00 1.013 0.005

0.7

05/25/09 5,564,670.7 237.7 1,840.0 305.5 25 60.00 0.909 0.004

1.0

05/25/09 5,575,015.6 239.4 1,840.0 303.0 25 60.00 0.804 0.004

1.1

05/25/09 5,579,407.9 240.4 1,840.0 306.2 25 60.00 1.137 0.006

1.1

05/25/09 5,622,265.9 240.7 1,840.0 305.5 25 60.00 1.263 0.006

1.2

05/25/09 5,607,408.9 242.1 1,840.0 301.7 25 60.00 1.276 0.006

1.3

05/25/09 5,509,132.5 246.3 1,840.0 302.4 25 60.00 1.364 0.007

1.3

05/25/09 5,551,329.1 258.1 1,840.0 304.7 25 60.00 1.478 0.007

1.4

05/24/09 7,228,451.1 274.7 1,840.0 400.7 36 60.00 1.463 0.009

1.5

05/24/09 9,370,761.8 280.2 1,840.0 575.5 50 60.00 1.422 0.013

1.5

05/24/09 9,409,220.4 280.8 1,840.0 577.8 50 60.00 1.524 0.014

1.5

05/24/09 9,412,202.2 279.8 1,840.0 578.0 50 60.00 1.524 0.014

1.6

05/24/09 9,338,451.0 277.4 1,840.0 578.6 50 60.00 1.511 0.014

1.5

05/24/09 9,369,777.0 276.1 1,840.0 580.5 50 60.00 1.611 0.015

1.3

05/24/09 9,406,723.3 274.7 1,840.0 577.7 50 60.00 1.524 0.014

1.2

05/24/09 8,826,051.9 267.7 1,840.0 532.4 46 60.00 1.345 0.011

1.3

05/24/09 7,992,417.5 265.0 1,840.0 469.1 40 60.00 1.276 0.010

1.3

05/24/09 7,988,960.6 265.2 1,840.0 464.6 40 60.00 1.395 0.010

1.0

05/24/09 8,237,663.5 267.5 1,840.0 479.1 42 60.00 1.395 0.011

0.9

05/24/09 8,256,657.7 266.6 1,840.0 480.2 42 60.00 1.073 0.008

0.9

05/24/09 8,098,516.5 270.5 1,840.0 475.4 42 60.00 0.957 0.007

0.7

05/24/09 8,864,019.8 274.3 1,840.0 534.7 46 60.00 0.931 0.008

05/24/09 9,131,871.7 280.3 1,840.0 555.9 48 60.00 0.718 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00 M

10:00 S S S

11:00 S S SC

12:00 S S SC

13:00 *M M * S S* S

14:00 C

15:00 S S SC

16:00 S S SC

17:00 C

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00 C

07:00 ST ST STC

08:00 ST ST STC

09:00 ST ST STC

10:00 ST ST 0.6 STC

0.6

05/27/09 9,896,291.5 286.5 1,840.0 607.7 55 60.00 0.610 0.006

0.6

05/27/09 9,910,870.4 286.6 1,840.0 603.3 55 60.00 0.615 0.006

0.6

05/27/09 9,900,074.1 284.5 1,840.0 602.6 55 60.00 0.615 0.006

0.4

05/27/09 9,905,245.3 280.3 1,840.0 608.3 55 60.00 0.610 0.006

0.3

05/27/09 9,932,596.4 268.4 1,840.0 610.0 55 60.00 0.406 0.004

0.3

05/27/09 7,475,530.6 243.8 1,840.0 434.7 37 60.00 0.322 0.002

0.3

05/27/09 5,482,696.0 240.6 1,840.0 301.0 26 60.00 0.341 0.002

0.3

05/27/09 5,515,111.3 243.0 1,840.0 299.7 26 60.00 0.344 0.002

0.3

05/27/09 5,612,694.3 244.8 1,840.0 302.0 26 60.00 0.348 0.002

0.2

05/27/09 5,788,082.3 246.1 1,840.0 302.0 26 60.00 0.359 0.002

0.2

05/27/09 5,727,122.5 248.1 1,840.0 308.1 26 60.00 0.232 0.001

0.3

05/26/09 5,556,289.9 253.4 1,840.0 302.0 26 60.00 0.230 0.001

0.5

05/26/09 5,475,888.1 266.6 1,840.0 297.6 26 60.00 0.344 0.002

0.6

05/26/09 7,735,724.2 283.1 1,840.0 433.0 39 60.00 0.557 0.004

0.6

05/26/09 9,493,245.1 288.3 1,840.0 577.8 51 60.00 0.615 0.006

0.7

05/26/09 9,581,609.3 289.2 1,840.0 578.0 52 60.00 0.621 0.006

0.7

05/26/09 9,623,592.2 289.6 1,840.0 585.8 52 60.00 0.718 0.007

14.1

05/26/09 9,865,084.0 290.2 1,840.0 605.8 54 60.00 0.711 0.007

14.1

05/26/09 9,946,357.1 289.1 1,840.0 616.2 55 60.00 14.201 0.140

27.5

05/26/09 9,919,303.8 287.5 1,840.0 614.5 55 60.00 14.201 0.140

14.5

05/26/09 9,944,770.4 285.7 1,840.0 610.8 55 60.00 27.942 0.273

14.5

05/26/09 9,924,645.2 284.4 1,840.0 598.7 55 60.00 14.998 0.144

14.5

05/26/09 9,998,418.4 287.1 1,840.0 603.1 55 60.00 14.998 0.145

14.5

05/26/09 10,056,987.7 288.0 1,840.0 650.4 55 60.00 13.990 0.146

1.5

05/26/09 10,101,876.9 287.0 1,840.0 647.8 55 60.00 14.109 0.146

1.7

05/26/09 10,100,901.4 285.3 1,840.0 631.3 55 60.00 1.498 0.015

1.7

05/26/09 10,105,193.9 284.3 1,840.0 620.6 55 60.00 1.727 0.017

1.6

05/26/09 10,146,627.0 281.2 1,840.0 634.2 55 60.00 1.697 0.017

1.4

05/26/09 10,136,818.8 261.9 1,840.0 633.6 54 60.00 1.597 0.016

1.9

05/26/09 6,509,509.8 237.2 1,840.0 346.7 29 60.00 1.640 0.009

1.7

05/26/09 5,816,374.1 235.5 1,840.0 290.8 24 60.00 2.371 0.011

1.4

05/26/09 5,707,310.3 235.4 1,840.0 291.6 24 60.00 2.076 0.010

0.9

05/26/09 5,624,013.6 237.4 1,840.0 293.4 24 60.00 1.674 0.008

0.9

05/26/09 5,516,589.3 241.4 1,840.0 287.8 24 60.00 1.076 0.005

1.1

05/26/09 5,422,071.0 245.8 1,840.0 291.7 24 60.00 1.044 0.005

1.1

05/25/09 5,482,214.6 254.0 1,840.0 295.0 24 60.00 1.276 0.006

05/25/09 5,555,726.0 268.4 1,840.0 292.9 25 60.00 1.302 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

11:00 ST ST STC

12:00 C

13:00 C

14:00 C

15:00

16:00

17:00

18:00

19:00

20:00

21:00 C

22:00 C

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00 C

13:00 S S SC

14:00 C

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00 0.6

1.0

05/28/09 5,639,681.3 265.3 1,840.0 300.4 26 60.00 0.703 0.003

1.1

05/28/09 8,101,166.3 280.7 1,840.0 453.5 42 60.00 1.115 0.008

1.1

05/28/09 9,597,699.4 283.5 1,840.0 579.0 52 60.00 1.138 0.011

1.0

05/28/09 9,639,903.1 281.8 1,840.0 581.5 52 60.00 1.138 0.011

0.9

05/28/09 9,732,672.0 282.5 1,840.0 576.6 52 60.00 1.053 0.010

0.9

05/28/09 9,584,351.2 283.1 1,840.0 567.7 52 60.00 0.948 0.009

0.8

05/28/09 9,634,483.3 282.2 1,840.0 565.5 52 60.00 0.957 0.009

0.8

05/28/09 9,625,743.9 280.3 1,840.0 565.0 52 60.00 0.850 0.008

0.7

05/28/09 9,605,488.6 279.8 1,840.0 563.8 52 60.00 0.850 0.008

0.6

05/28/09 9,436,546.7 279.1 1,840.0 569.3 52 60.00 0.724 0.007

0.5

05/28/09 9,576,017.8 276.6 1,840.0 577.7 52 60.00 0.621 0.006

0.3

05/28/09 9,509,246.4 261.9 1,840.0 568.5 50 60.00 0.522 0.005

0.2

05/28/09 6,650,228.3 241.2 1,840.0 372.3 32 60.00 0.334 0.002

0.2

05/28/09 5,515,029.5 240.6 1,840.0 290.7 25 60.00 0.237 0.001

0.1

05/28/09 5,393,807.6 239.2 1,840.0 293.2 25 60.00 0.230 0.001

0.2

05/28/09 5,353,300.2 238.6 1,840.0 290.9 25 60.00 0.115 0.001

0.2

05/28/09 5,317,809.3 239.3 1,840.0 289.0 25 60.00 0.230 0.001

0.1

05/28/09 5,356,471.5 239.5 1,840.0 291.1 25 60.00 0.230 0.001

0.1

05/28/09 5,346,713.2 238.8 1,840.0 287.7 25 60.00 0.116 0.001

0.2

05/28/09 5,405,289.3 239.0 1,840.0 290.8 25 60.00 0.116 0.001

0.2

05/28/09 5,381,811.0 240.5 1,840.0 286.7 25 60.00 0.234 0.001

0.1

05/28/09 5,425,889.0 241.8 1,840.0 283.1 25 60.00 0.239 0.001

0.1

05/28/09 5,505,447.2 242.7 1,840.0 293.2 25 60.00 0.117 0.001

0.2

05/28/09 5,440,342.8 245.6 1,840.0 286.8 25 60.00 0.118 0.001

0.3

05/27/09 5,637,284.9 252.4 1,840.0 297.2 26 60.00 0.237 0.001

0.7

05/27/09 5,609,258.7 264.1 1,840.0 295.7 25 60.00 0.355 0.002

0.8

05/27/09 7,037,888.6 281.1 1,840.0 374.9 34 60.00 0.820 0.005

0.8

05/27/09 10,075,350.7 286.2 1,840.0 624.2 55 60.00 0.806 0.008

0.6

05/27/09 10,090,064.1 285.4 1,840.0 630.6 56 60.00 0.799 0.008

0.6

05/27/09 9,884,376.6 284.7 1,840.0 612.4 55 60.00 0.604 0.006

0.6

05/27/09 9,901,663.7 284.3 1,840.0 608.1 55 60.00 0.610 0.006

0.7

05/27/09 9,915,584.3 283.7 1,840.0 609.0 55 60.00 0.610 0.006

0.7

05/27/09 9,918,830.6 285.1 1,840.0 609.2 55 60.00 0.711 0.007

0.6

05/27/09 9,922,112.8 285.5 1,840.0 609.3 55 60.00 0.711 0.007

0.7

05/27/09 9,924,057.0 285.0 1,840.0 604.1 55 60.00 0.615 0.006

0.6

05/27/09 9,864,477.7 283.8 1,840.0 605.8 55 60.00 0.711 0.007

05/27/09 9,879,057.3 285.2 1,840.0 606.7 55 60.00 0.610 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00 0.7

0.8

05/30/09 5,560,934.7 242.3 1,840.0 290.1 24 60.00 0.837 0.004

0.7

05/30/09 5,608,427.2 240.6 1,840.0 292.6 24 60.00 0.957 0.004

0.7

05/30/09 5,611,350.0 238.9 1,840.0 292.7 24 60.00 0.837 0.004

0.5

05/30/09 5,553,045.8 239.0 1,840.0 289.7 24 60.00 0.837 0.004

0.4

05/30/09 5,501,252.3 238.6 1,840.0 290.0 24 60.00 0.592 0.003

0.3

05/30/09 5,465,786.9 237.5 1,840.0 288.2 24 60.00 0.473 0.002

0.5

05/30/09 5,474,110.6 237.0 1,840.0 285.6 24 60.00 0.359 0.002

0.3

05/30/09 5,445,955.8 237.8 1,840.0 284.1 24 60.00 0.598 0.003

0.2

05/30/09 5,602,474.0 237.5 1,840.0 289.2 24 60.00 0.363 0.002

0.2

05/30/09 5,462,626.3 236.8 1,840.0 285.0 24 60.00 0.239 0.001

0.2

05/30/09 5,496,877.7 237.8 1,840.0 283.8 24 60.00 0.242 0.001

0.2

05/30/09 5,455,388.5 239.9 1,840.0 284.6 24 60.00 0.239 0.001

0.3

05/30/09 5,483,956.3 243.2 1,840.0 286.1 24 60.00 0.239 0.001

0.5

05/29/09 5,474,387.7 250.6 1,840.0 285.6 24 60.00 0.359 0.002

0.8

05/29/09 5,588,841.3 265.6 1,840.0 288.6 24 60.00 0.604 0.003

0.8

05/29/09 8,896,556.7 277.4 1,840.0 517.4 47 60.00 0.858 0.007

0.9

05/29/09 9,394,451.4 278.8 1,840.0 561.6 50 60.00 0.835 0.007

0.9

05/29/09 9,367,745.8 278.3 1,840.0 565.1 50 60.00 0.931 0.008

0.8

05/29/09 9,399,404.1 278.0 1,840.0 561.9 50 60.00 0.939 0.008

0.8

05/29/09 9,418,572.3 279.0 1,840.0 563.1 50 60.00 0.835 0.008

0.8

05/29/09 9,449,352.6 278.6 1,840.0 564.9 50 60.00 0.835 0.008

0.7

05/29/09 9,509,040.5 277.7 1,840.0 563.3 50 60.00 0.843 0.008

0.7

05/29/09 9,478,304.3 278.1 1,840.0 561.5 50 60.00 0.737 0.007

0.7

05/29/09 9,504,698.6 278.9 1,840.0 563.1 50 60.00 0.737 0.007

0.8

05/29/09 9,515,909.4 279.1 1,840.0 563.7 50 60.00 0.737 0.007

0.8

05/29/09 9,508,640.4 278.8 1,840.0 563.3 50 60.00 0.843 0.008

0.7

05/29/09 9,526,358.6 279.7 1,840.0 559.1 50 60.00 0.850 0.008

0.6

05/29/09 9,498,639.0 278.1 1,840.0 567.9 50 60.00 0.731 0.007

0.6

05/29/09 9,555,477.3 269.8 1,840.0 566.0 50 60.00 0.632 0.006

0.8

05/29/09 8,179,781.2 246.9 1,840.0 475.7 40 60.00 0.644 0.005

0.5

05/29/09 5,810,260.6 240.9 1,840.0 309.4 26 60.00 0.937 0.005

0.4

05/29/09 5,771,932.5 242.7 1,840.0 307.4 26 60.00 0.586 0.003

0.3

05/29/09 5,846,331.3 244.5 1,840.0 308.2 26 60.00 0.473 0.002

0.3

05/29/09 5,845,567.8 244.6 1,840.0 311.4 26 60.00 0.351 0.002

0.2

05/29/09 5,808,912.7 244.7 1,840.0 306.2 26 60.00 0.355 0.002

0.3

05/29/09 5,729,249.8 246.0 1,840.0 305.1 26 60.00 0.234 0.001

05/29/09 5,641,248.5 251.6 1,840.0 306.6 26 60.00 0.344 0.002
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 0.4

0.4

06/01/09 5,336,501.8 239.2 1,840.0 284.3 24 60.00 0.469 0.002

0.6

06/01/09 5,329,001.4 239.0 1,840.0 283.8 24 60.00 0.469 0.002

0.6

05/31/09 5,370,790.5 238.6 1,840.0 283.1 24 60.00 0.710 0.003

0.6

05/31/09 5,387,045.9 238.5 1,840.0 284.0 24 60.00 0.710 0.003

0.5

05/31/09 5,417,431.5 239.3 1,840.0 285.6 24 60.00 0.710 0.003

0.5

05/31/09 5,454,712.5 239.0 1,840.0 290.5 24 60.00 0.586 0.003

0.5

05/31/09 5,436,362.6 238.4 1,840.0 286.6 24 60.00 0.592 0.003

0.6

05/31/09 5,392,114.5 238.2 1,840.0 287.2 24 60.00 0.586 0.003

0.4

05/31/09 5,421,590.7 238.5 1,840.0 285.8 24 60.00 0.710 0.003

0.3

05/31/09 5,502,192.9 237.4 1,840.0 287.1 24 60.00 0.478 0.002

0.5

05/31/09 5,381,820.8 236.3 1,840.0 283.7 24 60.00 0.355 0.002

0.5

05/31/09 5,526,742.5 237.1 1,840.0 282.4 24 60.00 0.611 0.003

0.3

05/31/09 5,702,636.4 238.7 1,840.0 285.1 24 60.00 0.624 0.003

0.3

05/31/09 5,457,326.3 238.2 1,840.0 287.7 24 60.00 0.355 0.002

0.4

05/31/09 5,371,104.6 236.8 1,840.0 286.1 24 60.00 0.351 0.002

0.4

05/31/09 5,308,607.8 235.4 1,840.0 282.8 24 60.00 0.469 0.002

0.3

05/31/09 5,272,835.2 235.6 1,840.0 283.7 24 60.00 0.464 0.002

0.2

05/31/09 5,312,587.8 237.2 1,840.0 283.0 24 60.00 0.351 0.002

0.2

05/31/09 5,316,482.6 237.0 1,840.0 283.1 24 60.00 0.234 0.001

0.2

05/31/09 5,338,958.6 235.8 1,840.0 284.4 24 60.00 0.234 0.001

0.4

05/31/09 5,296,730.1 234.6 1,840.0 282.1 24 60.00 0.234 0.001

0.3

05/31/09 5,278,855.0 234.7 1,840.0 281.2 24 60.00 0.469 0.002

0.3

05/31/09 5,389,401.6 235.2 1,840.0 281.2 24 60.00 0.359 0.002

0.3

05/31/09 5,423,397.7 235.6 1,840.0 285.9 24 60.00 0.355 0.002

0.4

05/31/09 5,401,174.6 236.5 1,840.0 284.7 24 60.00 0.355 0.002

0.5

05/31/09 5,351,240.0 238.7 1,840.0 282.1 24 60.00 0.473 0.002

0.5

05/30/09 5,434,413.2 244.4 1,840.0 286.5 24 60.00 0.592 0.003

0.6

05/30/09 5,448,981.9 254.6 1,840.0 281.3 24 60.00 0.604 0.003

0.8

05/30/09 6,429,041.2 270.2 1,840.0 342.4 31 60.00 0.703 0.004

0.7

05/30/09 9,328,042.8 276.5 1,840.0 557.7 50 60.00 0.835 0.007

0.5

05/30/09 9,344,161.3 277.3 1,840.0 558.6 50 60.00 0.731 0.007

0.5

05/30/09 9,426,804.6 272.8 1,840.0 558.4 50 60.00 0.527 0.005

0.8

05/30/09 8,500,620.2 251.3 1,840.0 499.0 43 60.00 0.532 0.004

0.7

05/30/09 5,371,083.6 241.1 1,840.0 286.1 24 60.00 0.937 0.004

0.6

05/30/09 5,329,829.6 240.6 1,840.0 286.8 24 60.00 0.812 0.004

0.6

05/30/09 5,347,978.5 241.4 1,840.0 284.8 24 60.00 0.703 0.003

05/30/09 5,410,743.2 242.8 1,840.0 285.3 24 60.00 0.710 0.003
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00 M

10:00 M

11:00 S S S

12:00 M

13:00 S S SC

14:00

15:00

16:00

17:00

18:00

19:00

20:00 S S S

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00 S S S

09:00 M

10:00

11:00 C

12:00 C

13:00

14:00 1.1

1.0

06/02/09 9,307,607.1 277.0 1,840.0 561.5 50 60.00 1.138 0.010

1.0

06/02/09 9,358,081.2 277.7 1,840.0 564.5 50 60.00 1.034 0.009

0.9

06/02/09 9,331,714.9 277.4 1,840.0 568.0 50 60.00 1.025 0.009

0.9

06/02/09 9,350,375.2 276.4 1,840.0 569.1 50 60.00 0.923 0.008

0.9

06/02/09 9,323,475.6 275.2 1,840.0 567.5 50 60.00 0.923 0.008

0.8

06/02/09 9,368,620.4 276.0 1,840.0 565.2 50 60.00 0.931 0.008

0.7

06/02/09 9,330,210.4 275.1 1,840.0 567.9 50 60.00 0.820 0.007

0.7

06/02/09 9,331,181.6 272.0 1,840.0 568.0 50 60.00 0.718 0.007

0.4

06/02/09 9,345,978.0 264.6 1,840.0 568.9 50 60.00 0.718 0.007

0.3

06/02/09 8,678,515.1 244.6 1,840.0 528.3 46 60.00 0.410 0.003

0.3

06/02/09 5,478,472.9 235.6 1,840.0 288.8 24 60.00 0.355 0.002

0.3

06/02/09 5,491,821.1 235.6 1,840.0 289.5 24 60.00 0.355 0.002

0.3

06/02/09 5,523,726.1 237.2 1,840.0 288.2 24 60.00 0.359 0.002

0.2

06/02/09 5,556,425.4 238.6 1,840.0 292.9 24 60.00 0.355 0.002

0.2

06/02/09 5,520,610.9 240.4 1,840.0 291.1 24 60.00 0.237 0.001

0.4

06/01/09 5,520,984.7 246.1 1,840.0 291.1 24 60.00 0.237 0.001

0.9

06/01/09 5,467,413.0 259.9 1,840.0 288.2 24 60.00 0.473 0.002

1.1

06/01/09 7,673,444.4 274.0 1,840.0 433.7 39 60.00 0.994 0.007

1.2

06/01/09 9,344,666.4 275.6 1,840.0 563.7 50 60.00 1.138 0.010

1.2

06/01/09 9,349,725.0 274.5 1,840.0 564.0 50 60.00 1.241 0.011

1.1

06/01/09 9,317,817.6 275.3 1,840.0 562.1 50 60.00 1.241 0.011

1.1

06/01/09 9,330,491.5 276.9 1,840.0 562.8 50 60.00 1.138 0.010

1.1

06/01/09 9,496,200.0 277.4 1,840.0 567.7 50 60.00 1.148 0.010

1.0

06/01/09 9,498,845.5 277.5 1,840.0 562.7 50 60.00 1.159 0.010

0.9

06/01/09 9,581,590.9 279.8 1,840.0 572.8 50 60.00 1.044 0.010

0.8

06/01/09 9,641,342.6 281.5 1,840.0 576.4 51 60.00 0.939 0.009

0.9

06/01/09 9,709,806.2 282.1 1,840.0 580.5 52 60.00 0.835 0.008

1.0

06/01/09 9,632,190.6 279.6 1,840.0 575.8 50 60.00 0.939 0.009

0.9

06/01/09 9,592,066.9 279.8 1,840.0 573.4 50 60.00 1.044 0.010

0.6

06/01/09 9,501,412.1 278.6 1,840.0 568.0 49 60.00 0.939 0.009

0.4

06/01/09 9,531,429.8 270.0 1,840.0 564.6 49 60.00 0.632 0.006

0.4

06/01/09 8,359,924.2 247.0 1,840.0 477.1 42 60.00 0.437 0.003

0.4

06/01/09 5,587,669.2 240.1 1,840.0 294.6 25 60.00 0.473 0.002

0.3

06/01/09 5,480,361.7 239.9 1,840.0 291.9 25 60.00 0.469 0.002

0.3

06/01/09 5,383,699.3 238.7 1,840.0 283.8 24 60.00 0.355 0.002

0.4

06/01/09 5,375,162.8 237.6 1,840.0 283.4 24 60.00 0.355 0.002

06/01/09 5,255,100.1 238.1 1,840.0 274.2 24 60.00 0.478 0.002
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

15:00

16:00

17:00 S S S

18:00 C

19:00 C

20:00 C

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S 0.4 S

0.4

06/04/09 5,489,554.0 231.3 1,840.0 280.5 24 60.00 0.489 0.002

0.5

06/04/09 5,454,128.5 233.3 1,840.0 281.6 24 60.00 0.483 0.002

0.4

06/04/09 5,509,138.7 236.4 1,840.0 281.4 24 60.00 0.611 0.003

0.6

06/04/09 5,501,613.3 239.9 1,840.0 281.1 24 60.00 0.489 0.002

0.8

06/03/09 5,521,608.1 247.1 1,840.0 282.1 24 60.00 0.733 0.003

0.9

06/03/09 5,566,249.8 261.9 1,840.0 275.3 24 60.00 1.009 0.004

0.9

06/03/09 8,340,219.1 275.2 1,840.0 471.4 43 60.00 0.994 0.007

1.1

06/03/09 9,228,255.3 276.4 1,840.0 561.7 50 60.00 0.923 0.008

1.1

06/03/09 9,269,409.8 275.2 1,840.0 569.2 50 60.00 1.118 0.010

1.1

06/03/09 9,219,417.4 274.8 1,840.0 571.2 50 60.00 1.108 0.010

1.0

06/03/09 9,231,855.4 275.1 1,840.0 572.0 50 60.00 1.108 0.010

1.2

06/03/09 9,230,717.4 274.7 1,840.0 566.9 50 60.00 1.016 0.009

1.2

06/03/09 9,242,126.5 274.2 1,840.0 572.6 50 60.00 1.209 0.011

1.1

06/03/09 9,261,254.4 274.4 1,840.0 568.7 50 60.00 1.219 0.011

1.0

06/03/09 9,214,649.3 274.8 1,840.0 570.9 50 60.00 1.108 0.010

0.9

06/03/09 9,195,017.3 274.8 1,840.0 569.7 50 60.00 1.007 0.009

0.9

06/03/09 9,267,196.0 273.8 1,840.0 569.1 50 60.00 0.914 0.008

0.9

06/03/09 9,367,686.4 274.9 1,840.0 585.5 52 60.00 0.899 0.008

0.6

06/03/09 9,757,069.1 273.5 1,840.0 615.1 55 60.00 0.891 0.009

0.4

06/03/09 9,750,601.8 262.3 1,840.0 609.4 54 60.00 0.599 0.006

0.5

06/03/09 7,690,482.9 239.5 1,840.0 451.4 39 60.00 0.425 0.003

0.5

06/03/09 5,415,192.8 235.4 1,840.0 285.5 24 60.00 0.592 0.003

0.7

06/03/09 5,460,684.7 235.8 1,840.0 290.9 24 60.00 0.586 0.003

0.5

06/03/09 5,422,360.9 235.6 1,840.0 285.8 24 60.00 0.829 0.004

0.6

06/03/09 5,509,653.5 235.6 1,840.0 287.5 24 60.00 0.598 0.003

0.5

06/03/09 5,440,050.0 236.8 1,840.0 283.8 24 60.00 0.718 0.003

0.5

06/03/09 5,491,237.9 237.3 1,840.0 289.5 24 60.00 0.592 0.003

0.5

06/03/09 5,505,149.6 237.6 1,840.0 293.2 24 60.00 0.586 0.003

0.9

06/02/09 5,404,335.9 238.2 1,840.0 287.8 24 60.00 0.586 0.003

0.6

06/02/09 5,406,176.1 239.8 1,840.0 290.9 24 60.00 1.044 0.005

0.6

06/02/09 5,427,664.5 242.7 1,840.0 289.1 24 60.00 0.703 0.003

0.6

06/02/09 5,461,361.4 247.1 1,840.0 290.9 24 60.00 0.703 0.003

1.0

06/02/09 5,472,479.8 257.0 1,840.0 291.4 24 60.00 0.703 0.003

1.0

06/02/09 6,368,100.1 270.6 1,840.0 339.2 31 60.00 1.172 0.006

1.1

06/02/09 9,262,533.6 277.4 1,840.0 558.8 50 60.00 1.034 0.009

0.9

06/02/09 9,259,664.9 278.1 1,840.0 563.7 50 60.00 1.128 0.010

06/02/09 9,289,918.3 277.8 1,840.0 565.5 50 60.00 0.923 0.008
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00 0.9

0.8

06/05/09 9,403,805.3 285.9 1,840.0 567.3 50 60.00 0.931 0.008

0.7

06/05/09 9,377,216.3 285.1 1,840.0 565.7 50 60.00 0.828 0.007

0.7

06/05/09 9,358,262.6 285.5 1,840.0 559.4 50 60.00 0.731 0.007

0.7

06/05/09 9,390,011.7 284.8 1,840.0 561.4 50 60.00 0.731 0.007

0.8

06/05/09 9,371,251.6 282.5 1,840.0 555.1 50 60.00 0.737 0.007

0.7

06/05/09 9,261,486.5 280.8 1,840.0 553.6 50 60.00 0.835 0.007

0.7

06/05/09 9,356,318.8 281.1 1,840.0 554.2 50 60.00 0.737 0.007

0.6

06/05/09 9,343,654.2 280.3 1,840.0 558.6 50 60.00 0.731 0.007

0.6

06/05/09 9,334,386.7 277.4 1,840.0 558.0 50 60.00 0.626 0.006

0.5

06/05/09 9,277,081.3 270.9 1,840.0 554.6 50 60.00 0.626 0.006

0.3

06/05/09 9,409,608.0 257.2 1,840.0 567.7 50 60.00 0.517 0.005

0.2

06/05/09 6,512,446.7 238.6 1,840.0 364.5 32 60.00 0.334 0.002

0.3

06/05/09 5,382,543.1 237.7 1,840.0 277.9 24 60.00 0.242 0.001

0.3

06/05/09 5,390,963.0 239.0 1,840.0 278.3 24 60.00 0.363 0.002

0.3

06/05/09 5,369,649.7 241.6 1,840.0 277.3 24 60.00 0.363 0.002

0.4

06/05/09 5,369,598.4 243.5 1,840.0 280.2 24 60.00 0.359 0.002

0.6

06/05/09 5,448,758.3 247.3 1,840.0 281.3 24 60.00 0.483 0.002

0.9

06/04/09 5,371,084.7 255.8 1,840.0 283.1 24 60.00 0.710 0.003

0.9

06/04/09 5,841,191.6 271.3 1,840.0 292.1 26 60.00 1.123 0.005

1.1

06/04/09 9,195,648.1 283.0 1,840.0 554.8 49 60.00 0.931 0.008

1.1

06/04/09 9,383,877.5 284.7 1,840.0 571.2 50 60.00 1.128 0.010

1.2

06/04/09 9,383,067.3 285.0 1,840.0 571.1 50 60.00 1.128 0.010

1.2

06/04/09 9,379,402.8 283.7 1,840.0 570.9 50 60.00 1.230 0.011

1.1

06/04/09 9,337,890.2 282.2 1,840.0 568.4 50 60.00 1.230 0.011

1.1

06/04/09 9,350,182.0 282.7 1,840.0 569.1 50 60.00 1.128 0.010

1.3

06/04/09 9,326,674.8 284.0 1,840.0 572.8 50 60.00 1.118 0.010

1.1

06/04/09 9,472,976.3 285.8 1,840.0 581.8 51 60.00 1.321 0.012

0.9

06/04/09 9,593,318.7 284.3 1,840.0 589.1 52 60.00 1.118 0.011

1.0

06/04/09 9,592,330.6 281.6 1,840.0 589.1 52 60.00 0.914 0.009

0.9

06/04/09 9,606,751.2 279.7 1,840.0 590.0 52 60.00 1.016 0.010

0.8

06/04/09 9,560,004.3 277.8 1,840.0 587.1 52 60.00 0.914 0.009

0.8

06/04/09 9,327,552.4 277.3 1,840.0 583.0 52 60.00 0.799 0.007

0.8

06/04/09 9,524,624.8 276.0 1,840.0 585.0 52 60.00 0.813 0.008

0.6

06/04/09 9,421,359.5 269.4 1,840.0 583.7 52 60.00 0.806 0.008

0.3

06/04/09 9,459,055.0 256.1 1,840.0 586.0 52 60.00 0.604 0.006

0.3

06/04/09 6,763,860.9 234.5 1,840.0 378.6 32 60.00 0.334 0.002

06/04/09 5,386,372.1 232.2 1,840.0 283.9 24 60.00 0.355 0.002
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C 0.1 C

0.2

06/07/09 5,188,210.2 216.1 1,840.0 265.0 24 60.00 0.122 0.001

0.1

06/07/09 4,351,722.5 214.8 1,840.0 212.9 19 60.00 0.255 0.001

0.1

06/07/09 4,369,046.8 217.5 1,840.0 213.7 19 60.00 0.128 0.000

0.1

06/07/09 4,394,114.0 219.7 1,840.0 210.1 19 60.00 0.130 0.000

0.2

06/07/09 4,312,720.1 223.1 1,840.0 213.3 19 60.00 0.126 0.000

0.6

06/07/09 4,435,799.4 229.5 1,840.0 209.7 19 60.00 0.264 0.001

0.7

06/06/09 5,333,301.8 238.1 1,840.0 263.8 24 60.00 0.757 0.003

0.8

06/06/09 5,497,405.3 247.5 1,840.0 286.8 25 60.00 0.837 0.004

0.9

06/06/09 5,832,643.1 261.9 1,840.0 282.1 25 60.00 1.032 0.005

0.9

06/06/09 8,701,902.2 271.7 1,840.0 506.0 46 60.00 0.966 0.008

0.9

06/06/09 9,063,091.2 269.1 1,840.0 532.0 48 60.00 0.957 0.008

0.6

06/06/09 9,062,832.9 263.9 1,840.0 536.9 48 60.00 0.948 0.008

0.5

06/06/09 8,723,322.1 246.5 1,840.0 521.5 46 60.00 0.626 0.005

0.4

06/06/09 5,704,367.1 234.3 1,840.0 303.8 26 60.00 0.586 0.003

0.7

06/06/09 5,479,663.3 234.7 1,840.0 288.9 25 60.00 0.473 0.002

0.8

06/06/09 5,495,084.0 236.6 1,840.0 289.7 25 60.00 0.829 0.004

0.8

06/06/09 5,522,581.0 237.2 1,840.0 291.2 25 60.00 0.947 0.004

0.9

06/06/09 5,530,993.2 236.3 1,840.0 291.6 25 60.00 0.947 0.004

1.2

06/06/09 5,532,147.1 234.7 1,840.0 291.6 25 60.00 1.065 0.005

1.2

06/06/09 5,471,364.3 233.5 1,840.0 291.4 25 60.00 1.406 0.007

1.0

06/06/09 5,472,497.7 233.7 1,840.0 291.4 25 60.00 1.406 0.007

1.0

06/06/09 5,522,749.0 234.5 1,840.0 291.2 25 60.00 1.184 0.006

1.0

06/06/09 5,569,770.5 233.0 1,840.0 290.6 25 60.00 1.196 0.006

0.7

06/06/09 5,511,101.0 229.9 1,840.0 281.5 24 60.00 1.221 0.005

0.6

06/06/09 5,544,691.3 226.7 1,840.0 280.3 24 60.00 0.864 0.004

0.5

06/06/09 4,911,327.5 224.9 1,840.0 234.9 20 60.00 0.783 0.003

0.5

06/06/09 4,743,223.0 226.2 1,840.0 226.8 19 60.00 0.652 0.002

0.5

06/06/09 4,758,088.4 229.8 1,840.0 219.8 19 60.00 0.675 0.002

0.6

06/06/09 5,172,948.5 235.1 1,840.0 241.8 21 60.00 0.668 0.003

0.5

06/06/09 5,370,894.0 240.3 1,840.0 280.2 25 60.00 0.718 0.003

0.6

06/05/09 5,484,640.8 244.4 1,840.0 286.2 25 60.00 0.598 0.003

0.5

06/05/09 5,522,893.2 247.5 1,840.0 288.2 25 60.00 0.718 0.003

0.6

06/05/09 5,556,214.0 252.6 1,840.0 286.9 25 60.00 0.604 0.003

0.7

06/05/09 5,495,170.7 261.6 1,840.0 286.7 25 60.00 0.718 0.003

0.8

06/05/09 5,808,189.0 276.3 1,840.0 303.0 26 60.00 0.837 0.004

0.9

06/05/09 8,856,767.6 287.7 1,840.0 524.7 47 60.00 0.843 0.007

06/05/09 9,393,416.0 288.0 1,840.0 566.6 50 60.00 0.931 0.008
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00 M

09:00 S S S

10:00 M

11:00 C

12:00 S S SC

13:00 S S S

14:00 S S S

15:00 C

16:00 ST ST STC

17:00 ST ST ST

18:00 ST ST 1.3 STC

1.3

06/08/09 9,872,331.3 281.6 1,840.0 536.5 49 60.00 1.493 0.013

1.3

06/08/09 9,724,321.1 280.0 1,840.0 539.0 49 60.00 1.463 0.013

1.4

06/08/09 9,691,438.4 280.0 1,840.0 537.2 49 60.00 1.463 0.013

24.2

06/08/09 9,738,873.9 280.6 1,840.0 534.6 49 60.00 1.592 0.014

24.2

06/08/09 9,718,005.4 280.4 1,840.0 538.7 49 60.00 27.241 0.235

24.2

06/08/09 9,670,823.9 281.8 1,840.0 541.4 49 60.00 26.976 0.234

47.0

06/08/09 9,939,281.0 282.8 1,840.0 551.0 49 60.00 27.241 0.240

0.6

06/08/09 9,838,008.0 281.3 1,840.0 545.4 49 60.00 52.905 0.461

0.8

06/08/09 9,781,171.3 278.5 1,840.0 536.9 49 60.00 0.682 0.006

0.9

06/08/09 9,654,940.2 273.6 1,840.0 535.2 49 60.00 0.901 0.008

0.5

06/08/09 9,696,944.7 263.2 1,840.0 537.6 49 60.00 1.013 0.009

0.5

06/08/09 7,565,438.9 243.7 1,840.0 402.9 36 60.00 0.586 0.004

0.4

06/08/09 5,952,502.7 240.2 1,840.0 304.1 27 60.00 0.611 0.003

0.4

06/08/09 5,972,231.8 238.3 1,840.0 305.1 27 60.00 0.489 0.002

0.4

06/08/09 5,928,615.0 236.9 1,840.0 302.9 27 60.00 0.489 0.002

0.4

06/08/09 5,903,069.1 238.6 1,840.0 301.6 27 60.00 0.489 0.002

0.4

06/08/09 5,873,000.0 241.2 1,840.0 296.8 27 60.00 0.494 0.002

0.4

06/08/09 5,855,336.3 244.5 1,840.0 302.3 27 60.00 0.483 0.002

0.9

06/08/09 5,789,477.4 251.8 1,840.0 292.6 26 60.00 0.494 0.002

1.0

06/07/09 7,203,670.8 265.1 1,840.0 360.2 34 60.00 1.123 0.006

1.0

06/07/09 9,310,229.4 270.6 1,840.0 511.0 47 60.00 1.137 0.009

1.0

06/07/09 9,235,439.4 271.0 1,840.0 506.9 46 60.00 1.137 0.009

1.2

06/07/09 9,262,595.7 271.4 1,840.0 508.5 46 60.00 1.137 0.009

1.0

06/07/09 9,321,561.9 269.8 1,840.0 521.8 46 60.00 1.338 0.011

0.6

06/07/09 9,451,035.5 266.9 1,840.0 529.1 47 60.00 1.115 0.009

0.4

06/07/09 8,894,600.6 249.1 1,840.0 497.9 43 60.00 0.669 0.005

0.4

06/07/09 5,905,714.2 240.3 1,840.0 304.9 26 60.00 0.483 0.002

0.6

06/07/09 5,881,790.1 238.5 1,840.0 303.7 26 60.00 0.483 0.002

0.6

06/07/09 5,881,012.3 236.2 1,840.0 300.4 26 60.00 0.733 0.004

0.4

06/07/09 5,891,255.8 233.9 1,840.0 301.0 26 60.00 0.733 0.004

0.3

06/07/09 5,839,170.8 232.4 1,840.0 298.3 26 60.00 0.489 0.002

0.3

06/07/09 5,814,229.0 232.8 1,840.0 293.9 26 60.00 0.370 0.002

0.2

06/07/09 5,710,818.1 232.8 1,840.0 288.7 26 60.00 0.370 0.002

0.2

06/07/09 5,721,217.2 232.3 1,840.0 289.2 26 60.00 0.247 0.001

0.2

06/07/09 5,868,586.0 231.7 1,840.0 290.3 25 60.00 0.252 0.001

0.1

06/07/09 5,581,786.4 228.7 1,840.0 279.1 25 60.00 0.250 0.001

06/07/09 5,380,521.2 223.4 1,840.0 277.8 25 60.00 0.121 0.001
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

19:00 C

20:00 S S S

21:00 C

22:00 S S SC

23:00 C

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C S S SC

03:00 S S S

04:00 C

05:00 C C

06:00

07:00 0.7

0.6

06/10/09 5,803,852.0 242.8 1,840.0 299.7 25 60.00 0.846 0.004

0.4

06/10/09 5,822,969.5 243.3 1,840.0 297.5 25 60.00 0.733 0.003

0.5

06/10/09 5,839,271.8 244.8 1,840.0 295.1 25 60.00 0.494 0.002

0.7

06/10/09 5,833,404.3 247.4 1,840.0 294.8 25 60.00 0.617 0.003

0.7

06/10/09 5,880,653.8 250.6 1,840.0 300.4 25 60.00 0.855 0.004

0.9

06/10/09 5,712,699.0 259.7 1,840.0 291.9 25 60.00 0.855 0.004

0.9

06/10/09 6,000,472.9 275.4 1,840.0 296.7 26 60.00 1.136 0.005

1.1

06/10/09 9,783,060.0 285.3 1,840.0 558.3 49 60.00 0.984 0.009

1.4

06/09/09 9,866,005.2 285.0 1,840.0 557.6 50 60.00 1.214 0.011

1.3

06/09/09 9,873,102.3 283.0 1,840.0 558.0 50 60.00 1.546 0.014

1.3

06/09/09 9,948,043.5 284.5 1,840.0 556.9 50 60.00 1.449 0.013

1.3

06/09/09 10,038,261.9 286.6 1,840.0 556.5 50 60.00 1.463 0.013

1.3

06/09/09 10,026,455.5 286.8 1,840.0 561.2 50 60.00 1.449 0.013

1.4

06/09/09 10,022,583.1 289.0 1,840.0 561.1 50 60.00 1.449 0.013

1.5

06/09/09 10,007,130.0 291.7 1,840.0 565.6 50 60.00 1.546 0.014

1.6

06/09/09 10,133,468.9 293.2 1,840.0 578.2 52 60.00 1.640 0.015

1.8

06/09/09 10,159,199.9 292.7 1,840.0 579.7 52 60.00 1.750 0.016

1.8

06/09/09 10,131,753.6 290.8 1,840.0 578.2 52 60.00 1.968 0.018

1.4

06/09/09 10,193,502.0 287.8 1,840.0 576.2 52 60.00 1.987 0.018

1.2

06/09/09 10,002,813.4 285.1 1,840.0 570.8 52 60.00 1.531 0.014

1.2

06/09/09 10,030,714.4 286.2 1,840.0 572.4 52 60.00 1.312 0.012

1.3

06/09/09 10,149,876.9 288.6 1,840.0 573.7 52 60.00 1.325 0.012

1.3

06/09/09 10,428,357.6 287.4 1,840.0 583.7 52 60.00 1.449 0.014

1.2

06/09/09 10,248,610.2 284.5 1,840.0 573.7 52 60.00 1.449 0.013

1.1

06/09/09 10,298,124.3 282.4 1,840.0 582.1 52 60.00 1.325 0.012

1.1

06/09/09 10,184,612.5 278.5 1,840.0 570.1 50 60.00 1.226 0.011

1.0

06/09/09 10,084,266.9 276.4 1,840.0 564.5 50 60.00 1.226 0.011

1.0

06/09/09 10,117,082.7 275.4 1,840.0 560.8 50 60.00 1.126 0.010

0.9

06/09/09 9,812,621.2 270.1 1,840.0 538.6 48 60.00 1.137 0.010

1.0

06/09/09 8,572,390.1 264.5 1,840.0 447.2 40 60.00 1.076 0.008

1.0

06/09/09 8,485,317.4 265.1 1,840.0 447.3 40 60.00 1.184 0.008

1.1

06/09/09 8,579,070.3 267.0 1,840.0 452.3 40 60.00 1.184 0.009

1.3

06/08/09 8,547,680.2 268.0 1,840.0 446.0 40 60.00 1.316 0.009

1.4

06/08/09 8,556,635.8 268.9 1,840.0 451.1 40 60.00 1.539 0.011

1.4

06/08/09 9,215,282.0 270.9 1,840.0 485.8 43 60.00 1.657 0.013

1.3

06/08/09 9,333,376.1 275.3 1,840.0 512.3 46 60.00 1.592 0.013

06/08/09 9,703,324.0 279.3 1,840.0 537.9 48 60.00 1.463 0.013
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00 1.0

0.8

06/11/09 9,623,273.6 279.6 1,840.0 559.6 50 60.00 1.073 0.010

0.6

06/11/09 9,681,586.8 279.8 1,840.0 563.0 50 60.00 0.858 0.008

0.4

06/11/09 9,681,773.7 273.0 1,840.0 563.0 50 60.00 0.644 0.006

0.8

06/11/09 8,318,788.9 248.5 1,840.0 474.7 41 60.00 0.437 0.003

0.7

06/11/09 5,672,967.1 240.6 1,840.0 296.0 25 60.00 0.957 0.005

0.5

06/11/09 5,655,901.4 241.1 1,840.0 295.1 25 60.00 0.837 0.004

0.5

06/11/09 5,744,769.7 243.2 1,840.0 293.5 25 60.00 0.611 0.003

0.6

06/11/09 5,796,989.0 243.3 1,840.0 293.0 25 60.00 0.617 0.003

0.5

06/11/09 5,827,131.8 243.9 1,840.0 294.5 25 60.00 0.741 0.003

0.7

06/11/09 5,792,992.8 244.9 1,840.0 292.8 25 60.00 0.617 0.003

0.8

06/11/09 5,753,879.0 244.3 1,840.0 294.0 25 60.00 0.855 0.004

0.8

06/11/09 5,729,549.9 243.6 1,840.0 292.7 25 60.00 0.977 0.005

1.0

06/11/09 5,750,330.2 242.1 1,840.0 293.8 25 60.00 0.977 0.005

1.0

06/11/09 5,703,277.0 240.7 1,840.0 294.4 25 60.00 1.209 0.006

0.9

06/11/09 5,685,978.7 240.0 1,840.0 293.6 25 60.00 1.209 0.006

0.5

06/11/09 5,686,657.3 240.6 1,840.0 290.5 25 60.00 1.099 0.005

0.6

06/11/09 5,725,514.8 243.4 1,840.0 289.4 25 60.00 0.617 0.003

0.5

06/11/09 5,788,992.0 244.6 1,840.0 289.4 25 60.00 0.749 0.003

0.6

06/11/09 5,836,602.7 246.2 1,840.0 291.8 25 60.00 0.624 0.003

0.5

06/11/09 5,946,097.9 249.7 1,840.0 294.1 25 60.00 0.757 0.004

0.4

06/11/09 5,914,922.6 253.7 1,840.0 295.8 25 60.00 0.624 0.003

0.9

06/10/09 5,830,188.8 264.0 1,840.0 291.5 25 60.00 0.499 0.002

1.1

06/10/09 6,326,546.2 281.6 1,840.0 312.9 27 60.00 1.136 0.006

1.2

06/10/09 9,792,821.3 290.4 1,840.0 553.5 49 60.00 1.214 0.011

1.2

06/10/09 9,878,477.0 290.3 1,840.0 558.3 50 60.00 1.325 0.012

1.3

06/10/09 9,863,165.7 289.6 1,840.0 562.8 50 60.00 1.312 0.012

1.4

06/10/09 9,821,573.8 288.1 1,840.0 560.5 50 60.00 1.422 0.013

1.3

06/10/09 9,853,587.0 286.6 1,840.0 562.3 50 60.00 1.531 0.014

1.3

06/10/09 9,852,557.7 284.6 1,840.0 562.3 50 60.00 1.422 0.013

1.2

06/10/09 9,825,016.5 283.2 1,840.0 560.7 50 60.00 1.422 0.013

1.1

06/10/09 9,866,723.2 284.0 1,840.0 557.7 50 60.00 1.325 0.012

1.1

06/10/09 9,885,499.8 284.2 1,840.0 558.7 50 60.00 1.214 0.011

1.1

06/10/09 9,769,223.7 283.5 1,840.0 552.2 50 60.00 1.214 0.011

1.0

06/10/09 9,764,489.7 281.3 1,840.0 557.2 50 60.00 1.203 0.011

0.9

06/10/09 9,751,082.0 277.3 1,840.0 556.4 50 60.00 1.093 0.010

0.6

06/10/09 9,823,609.5 269.3 1,840.0 555.3 50 60.00 0.994 0.009

06/10/09 8,196,600.0 248.3 1,840.0 454.4 39 60.00 0.675 0.005
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00 0.8

0.6

06/13/09 5,746,032.4 242.2 1,840.0 290.4 24 60.00 0.988 0.005

0.5

06/13/09 5,783,680.4 243.4 1,840.0 289.2 24 60.00 0.749 0.003

0.4

06/13/09 5,757,304.8 244.3 1,840.0 291.0 24 60.00 0.617 0.003

0.6

06/13/09 5,708,815.3 243.6 1,840.0 288.6 24 60.00 0.494 0.002

0.7

06/13/09 5,808,375.3 242.9 1,840.0 287.2 24 60.00 0.757 0.003

0.6

06/13/09 5,840,370.8 243.1 1,840.0 288.8 24 60.00 0.883 0.004

0.5

06/13/09 5,804,182.4 245.2 1,840.0 287.0 24 60.00 0.757 0.003

0.4

06/13/09 5,862,503.9 246.0 1,840.0 277.2 24 60.00 0.660 0.003

0.5

06/13/09 5,769,259.2 246.9 1,840.0 285.3 24 60.00 0.505 0.002

1.0

06/13/09 5,877,964.6 248.7 1,840.0 290.7 24 60.00 0.631 0.003

1.0

06/12/09 5,776,686.4 253.9 1,840.0 285.7 24 60.00 1.262 0.006

1.0

06/12/09 6,015,931.5 266.6 1,840.0 304.1 26 60.00 1.235 0.006

1.0

06/12/09 8,816,615.2 276.7 1,840.0 493.6 43 60.00 1.115 0.009

1.0

06/12/09 9,027,896.2 276.7 1,840.0 505.4 45 60.00 1.115 0.009

1.1

06/12/09 9,022,110.7 274.4 1,840.0 509.9 45 60.00 1.104 0.009

0.8

06/12/09 8,953,912.4 273.1 1,840.0 506.1 44 60.00 1.214 0.010

0.8

06/12/09 8,987,542.3 274.9 1,840.0 503.1 44 60.00 0.892 0.007

0.9

06/12/09 9,014,479.2 274.3 1,840.0 504.6 45 60.00 0.892 0.007

0.8

06/12/09 8,955,626.9 271.4 1,840.0 506.2 44 60.00 0.994 0.008

0.6

06/12/09 8,935,798.4 270.2 1,840.0 505.1 44 60.00 0.883 0.007

0.6

06/12/09 9,008,532.5 268.5 1,840.0 504.3 45 60.00 0.669 0.005

1.0

06/12/09 9,081,514.8 256.0 1,840.0 508.4 44 60.00 0.669 0.005

0.8

06/12/09 6,259,229.4 242.4 1,840.0 323.2 27 60.00 1.209 0.006

0.5

06/12/09 5,784,624.1 244.5 1,840.0 295.5 25 60.00 0.977 0.005

0.5

06/12/09 5,867,377.8 245.4 1,840.0 296.5 25 60.00 0.617 0.003

0.8

06/12/09 5,862,724.5 243.5 1,840.0 296.3 25 60.00 0.617 0.003

0.8

06/12/09 5,807,670.8 241.9 1,840.0 296.7 25 60.00 0.977 0.005

0.6

06/12/09 5,734,388.7 242.7 1,840.0 292.9 25 60.00 0.977 0.005

0.5

06/12/09 5,811,779.6 245.3 1,840.0 293.8 25 60.00 0.741 0.003

0.6

06/12/09 5,858,038.5 246.0 1,840.0 296.1 25 60.00 0.617 0.003

0.6

06/12/09 5,873,610.7 245.2 1,840.0 293.7 25 60.00 0.749 0.004

0.8

06/12/09 5,780,277.8 246.0 1,840.0 289.0 25 60.00 0.749 0.003

0.5

06/12/09 5,804,247.0 250.7 1,840.0 290.2 25 60.00 0.998 0.005

0.7

06/12/09 5,903,261.9 260.4 1,840.0 291.9 25 60.00 0.631 0.003

1.0

06/11/09 6,115,520.9 274.6 1,840.0 292.5 25 60.00 0.913 0.004

1.2

06/11/09 9,320,471.8 283.4 1,840.0 526.8 47 60.00 1.104 0.009

06/11/09 9,660,489.2 281.2 1,840.0 561.8 50 60.00 1.288 0.012
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00 1.0

1.2

06/14/09 7,287,004.1 278.6 1,840.0 360.4 33 60.00 1.262 0.007

1.1

06/14/09 10,189,256.7 285.4 1,840.0 614.7 55 60.00 1.241 0.012

1.1

06/14/09 10,270,863.0 287.4 1,840.0 619.6 55 60.00 1.138 0.011

1.2

06/14/09 10,272,080.5 287.8 1,840.0 619.7 55 60.00 1.138 0.011

1.4

06/14/09 10,133,683.5 285.9 1,840.0 616.9 55 60.00 1.230 0.012

1.3

06/14/09 10,090,828.8 283.7 1,840.0 614.2 55 60.00 1.435 0.014

1.3

06/14/09 10,040,421.6 285.3 1,840.0 616.6 55 60.00 1.321 0.013

1.2

06/14/09 10,088,418.6 286.7 1,840.0 619.5 55 60.00 1.321 0.013

1.1

06/14/09 10,085,515.1 286.8 1,840.0 613.9 55 60.00 1.230 0.012

0.7

06/14/09 10,147,588.6 282.1 1,840.0 612.2 55 60.00 1.138 0.011

0.8

06/14/09 9,670,867.8 259.2 1,840.0 588.7 51 60.00 0.718 0.007

0.7

06/14/09 5,786,534.0 246.5 1,840.0 298.8 25 60.00 0.967 0.005

0.9

06/14/09 5,720,883.6 249.0 1,840.0 289.2 24 60.00 0.864 0.004

0.7

06/14/09 5,774,151.4 248.5 1,840.0 291.8 24 60.00 1.111 0.005

0.7

06/14/09 5,809,214.4 246.5 1,840.0 293.6 24 60.00 0.864 0.004

1.2

06/14/09 5,745,232.5 244.0 1,840.0 290.4 24 60.00 0.864 0.004

1.1

06/14/09 5,659,542.0 242.1 1,840.0 289.2 24 60.00 1.466 0.007

1.0

06/14/09 5,666,338.9 241.3 1,840.0 289.5 24 60.00 1.344 0.006

0.9

06/14/09 5,651,196.7 242.4 1,840.0 288.7 24 60.00 1.221 0.006

0.9

06/14/09 5,713,554.4 244.4 1,840.0 288.8 24 60.00 1.111 0.005

0.8

06/14/09 5,765,246.9 244.3 1,840.0 288.3 24 60.00 1.123 0.005

0.6

06/14/09 5,766,293.5 243.6 1,840.0 291.4 24 60.00 0.988 0.005

0.6

06/14/09 5,770,107.9 243.8 1,840.0 291.6 24 60.00 0.741 0.003

0.7

06/13/09 5,776,564.7 244.0 1,840.0 292.0 24 60.00 0.741 0.003

0.5

06/13/09 5,918,650.0 242.4 1,840.0 292.7 24 60.00 0.883 0.004

0.6

06/13/09 6,355,568.8 241.2 1,840.0 276.3 24 60.00 0.718 0.003

0.8

06/13/09 5,957,900.7 239.9 1,840.0 268.8 24 60.00 0.830 0.004

0.9

06/13/09 5,899,739.5 241.4 1,840.0 269.3 24 60.00 1.093 0.005

0.9

06/13/09 5,941,171.2 245.2 1,840.0 271.2 24 60.00 1.230 0.005

0.8

06/13/09 6,139,408.0 247.1 1,840.0 290.3 24 60.00 1.188 0.006

0.6

06/13/09 5,831,862.2 245.9 1,840.0 291.6 24 60.00 0.998 0.005

0.7

06/13/09 5,776,176.2 244.6 1,840.0 288.8 24 60.00 0.749 0.003

0.7

06/13/09 5,705,559.2 244.7 1,840.0 285.3 24 60.00 0.874 0.004

0.6

06/13/09 5,764,166.9 246.7 1,840.0 288.2 24 60.00 0.874 0.004

0.5

06/13/09 5,753,631.3 246.6 1,840.0 287.7 24 60.00 0.749 0.003

0.5

06/13/09 5,851,457.0 245.6 1,840.0 292.6 24 60.00 0.624 0.003

06/13/09 5,851,845.1 243.6 1,840.0 289.4 24 60.00 0.631 0.003
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00 S S S

20:00 S S S

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 0.8

0.6

06/16/09 5,819,769.1 242.5 1,840.0 297.3 25 60.00 0.977 0.005

0.5

06/16/09 5,830,221.3 241.5 1,840.0 301.0 25 60.00 0.725 0.003

0.5

06/16/09 5,835,495.8 239.8 1,840.0 298.1 25 60.00 0.611 0.003

0.6

06/16/09 5,771,001.0 239.7 1,840.0 294.8 25 60.00 0.611 0.003

0.4

06/16/09 5,825,801.5 239.4 1,840.0 297.6 25 60.00 0.733 0.003

0.5

06/16/09 5,765,773.9 238.4 1,840.0 294.6 25 60.00 0.489 0.002

0.5

06/16/09 5,844,290.7 237.8 1,840.0 295.4 25 60.00 0.617 0.003

0.6

06/16/09 5,750,156.1 239.3 1,840.0 290.6 25 60.00 0.617 0.003

0.6

06/16/09 5,788,714.3 241.2 1,840.0 292.6 25 60.00 0.741 0.003

0.7

06/16/09 5,935,242.3 241.2 1,840.0 300.0 25 60.00 0.741 0.004

0.8

06/16/09 5,885,925.9 240.6 1,840.0 297.5 25 60.00 0.864 0.004

0.9

06/16/09 5,772,450.4 240.5 1,840.0 294.9 25 60.00 0.977 0.005

0.7

06/15/09 5,743,328.3 243.5 1,840.0 296.5 25 60.00 1.088 0.005

0.9

06/15/09 5,822,934.9 247.9 1,840.0 294.3 25 60.00 0.864 0.004

1.0

06/15/09 5,854,335.5 253.1 1,840.0 295.9 25 60.00 1.111 0.005

1.0

06/15/09 5,910,124.5 265.2 1,840.0 295.5 25 60.00 1.248 0.006

1.2

06/15/09 8,326,826.4 279.8 1,840.0 452.6 41 60.00 1.148 0.008

1.2

06/15/09 9,681,979.7 283.3 1,840.0 568.3 50 60.00 1.276 0.012

1.3

06/15/09 9,716,254.7 283.6 1,840.0 570.3 50 60.00 1.276 0.012

1.4

06/15/09 9,701,606.7 282.4 1,840.0 569.5 50 60.00 1.382 0.013

1.3

06/15/09 9,677,378.4 280.3 1,840.0 568.0 50 60.00 1.488 0.014

1.2

06/15/09 9,730,343.3 281.2 1,840.0 571.1 50 60.00 1.382 0.013

1.1

06/15/09 9,736,039.7 281.3 1,840.0 571.5 50 60.00 1.276 0.012

1.0

06/15/09 9,748,089.9 280.2 1,840.0 572.2 50 60.00 1.169 0.011

1.1

06/15/09 9,707,418.9 278.7 1,840.0 569.8 50 60.00 1.063 0.010

1.1

06/15/09 9,714,822.1 279.6 1,840.0 570.2 50 60.00 1.169 0.011

1.0

06/15/09 9,662,564.5 279.5 1,840.0 567.2 50 60.00 1.169 0.011

1.0

06/15/09 9,724,536.7 276.5 1,840.0 570.8 50 60.00 1.063 0.010

0.7

06/15/09 9,711,884.8 265.6 1,840.0 570.1 50 60.00 1.063 0.010

1.0

06/15/09 8,150,514.1 243.7 1,840.0 456.3 39 60.00 0.780 0.006

0.8

06/15/09 5,762,149.6 239.1 1,840.0 278.7 23 60.00 1.290 0.006

0.7

06/15/09 5,741,092.4 239.0 1,840.0 277.7 23 60.00 1.032 0.005

0.9

06/15/09 5,754,648.1 239.0 1,840.0 275.2 23 60.00 0.913 0.004

0.7

06/15/09 5,683,876.4 241.7 1,840.0 268.8 23 60.00 1.188 0.005

0.6

06/15/09 5,749,072.4 245.2 1,840.0 275.0 23 60.00 0.913 0.004

0.6

06/15/09 5,753,845.9 250.1 1,840.0 278.3 23 60.00 0.774 0.003

06/14/09 5,762,472.9 261.4 1,840.0 275.6 23 60.00 0.783 0.003
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00 0.6

0.6

06/18/09 5,888,809.2 244.6 1,840.0 294.4 24 60.00 0.749 0.004

0.7

06/17/09 5,953,228.5 251.8 1,840.0 291.2 24 60.00 0.765 0.004

1.0

06/17/09 6,000,456.4 264.9 1,840.0 293.5 24 60.00 0.893 0.004

1.1

06/17/09 8,380,769.7 281.0 1,840.0 441.8 40 60.00 1.184 0.008

1.1

06/17/09 9,771,875.1 281.9 1,840.0 563.0 50 60.00 1.191 0.011

1.1

06/17/09 9,703,669.6 280.9 1,840.0 564.3 50 60.00 1.180 0.011

1.0

06/17/09 9,741,239.4 282.5 1,840.0 566.5 50 60.00 1.180 0.011

1.0

06/17/09 9,745,967.9 282.4 1,840.0 566.8 50 60.00 1.073 0.010

0.9

06/17/09 9,895,273.9 280.1 1,840.0 570.0 50 60.00 1.083 0.010

0.8

06/17/09 9,605,208.6 278.1 1,840.0 558.6 50 60.00 0.966 0.009

0.8

06/17/09 9,625,643.7 279.9 1,840.0 554.5 50 60.00 0.867 0.008

0.7

06/17/09 9,669,451.5 280.9 1,840.0 557.0 50 60.00 0.867 0.008

1.0

06/17/09 9,677,229.5 281.7 1,840.0 557.5 50 60.00 0.758 0.007

1.1

06/17/09 9,779,761.0 280.0 1,840.0 568.7 50 60.00 1.073 0.010

0.8

06/17/09 9,822,677.8 271.0 1,840.0 571.2 50 60.00 1.180 0.011

0.7

06/17/09 9,098,425.2 250.3 1,840.0 529.1 45 60.00 0.858 0.007

0.6

06/17/09 5,871,941.8 241.7 1,840.0 296.8 25 60.00 0.864 0.004

0.5

06/17/09 5,862,098.2 239.8 1,840.0 299.5 25 60.00 0.733 0.004

0.5

06/17/09 5,842,073.6 237.9 1,840.0 298.4 25 60.00 0.611 0.003

0.8

06/17/09 5,839,366.9 238.3 1,840.0 282.4 24 60.00 0.645 0.003

0.7

06/17/09 5,740,436.7 240.2 1,840.0 287.0 24 60.00 0.998 0.005

0.8

06/17/09 5,752,850.0 242.6 1,840.0 284.5 24 60.00 0.883 0.004

0.6

06/17/09 5,780,239.7 243.0 1,840.0 285.9 24 60.00 1.009 0.005

0.6

06/17/09 5,774,491.5 242.8 1,840.0 288.7 24 60.00 0.749 0.003

0.7

06/17/09 5,716,590.9 243.8 1,840.0 289.0 24 60.00 0.741 0.003

0.6

06/16/09 5,686,534.3 248.9 1,840.0 287.4 24 60.00 0.864 0.004

0.7

06/16/09 5,764,109.9 258.8 1,840.0 288.2 24 60.00 0.749 0.003

0.9

06/16/09 6,486,328.7 274.8 1,840.0 317.3 28 60.00 0.893 0.005

0.9

06/16/09 9,702,483.8 281.4 1,840.0 569.5 50 60.00 0.957 0.009

0.8

06/16/09 9,692,870.6 279.1 1,840.0 568.9 50 60.00 0.957 0.009

0.8

06/16/09 9,670,847.1 278.5 1,840.0 567.6 50 60.00 0.850 0.008

0.5

06/16/09 9,690,076.5 273.5 1,840.0 568.8 50 60.00 0.850 0.008

0.5

06/16/09 8,956,822.9 252.5 1,840.0 525.7 45 60.00 0.532 0.004

0.8

06/16/09 5,766,525.1 241.5 1,840.0 297.8 25 60.00 0.604 0.003

0.9

06/16/09 5,712,548.3 240.1 1,840.0 298.1 25 60.00 0.957 0.005

0.7

06/16/09 5,690,136.1 241.2 1,840.0 296.9 25 60.00 1.076 0.005

06/16/09 5,793,543.7 242.5 1,840.0 299.1 25 60.00 0.846 0.004
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00 0.9

0.9

06/19/09 9,706,331.6 278.2 1,840.0 548.6 50 60.00 0.994 0.009

1.0

06/19/09 9,720,721.2 277.9 1,840.0 549.4 50 60.00 0.994 0.009

1.1

06/19/09 9,677,491.8 278.4 1,840.0 547.0 50 60.00 1.104 0.010

1.1

06/19/09 9,766,248.8 280.3 1,840.0 552.0 50 60.00 1.214 0.011

1.0

06/19/09 9,741,954.0 280.2 1,840.0 550.6 50 60.00 1.214 0.011

1.2

06/19/09 9,756,533.3 279.0 1,840.0 551.5 50 60.00 1.104 0.010

1.0

06/19/09 9,754,243.7 275.9 1,840.0 546.0 50 60.00 1.338 0.012

0.7

06/19/09 9,907,421.2 264.9 1,840.0 565.3 50 60.00 1.093 0.010

0.8

06/19/09 7,817,983.7 244.5 1,840.0 424.9 37 60.00 0.804 0.005

0.7

06/19/09 5,904,127.9 242.5 1,840.0 292.0 24 60.00 1.009 0.005

0.7

06/19/09 5,895,778.3 242.9 1,840.0 291.6 24 60.00 0.883 0.004

1.1

06/19/09 5,950,059.2 243.9 1,840.0 291.0 24 60.00 0.893 0.004

0.8

06/19/09 5,862,120.7 247.7 1,840.0 289.9 24 60.00 1.388 0.006

0.8

06/19/09 5,851,238.7 258.8 1,840.0 286.2 24 60.00 1.021 0.005

1.2

06/18/09 6,366,547.7 276.3 1,840.0 308.0 27 60.00 1.032 0.005

1.5

06/18/09 9,760,025.8 284.2 1,840.0 557.0 49 60.00 1.312 0.012

1.5

06/18/09 9,824,403.2 283.4 1,840.0 560.6 50 60.00 1.640 0.015

1.4

06/18/09 9,861,106.8 281.5 1,840.0 562.7 50 60.00 1.640 0.015

1.4

06/18/09 9,842,845.9 281.5 1,840.0 561.7 50 60.00 1.531 0.014

1.2

06/18/09 9,878,651.9 284.8 1,840.0 563.7 50 60.00 1.531 0.014

1.3

06/18/09 9,927,069.5 286.0 1,840.0 566.5 50 60.00 1.312 0.012

1.3

06/18/09 9,951,113.6 285.5 1,840.0 567.9 50 60.00 1.422 0.013

1.4

06/18/09 9,920,866.6 283.5 1,840.0 566.1 50 60.00 1.422 0.013

1.4

06/18/09 9,931,854.7 280.2 1,840.0 566.8 50 60.00 1.531 0.014

1.1

06/18/09 9,917,152.5 275.5 1,840.0 565.9 50 60.00 1.531 0.014

0.7

06/18/09 9,892,318.6 269.9 1,840.0 564.5 50 60.00 1.203 0.011

0.7

06/18/09 9,955,296.3 256.2 1,840.0 573.5 49 60.00 0.758 0.007

0.6

06/18/09 6,133,374.1 239.5 1,840.0 316.6 26 60.00 0.846 0.004

0.6

06/18/09 5,869,925.4 238.1 1,840.0 290.3 24 60.00 0.757 0.004

0.9

06/18/09 5,906,987.8 236.3 1,840.0 288.9 24 60.00 0.765 0.004

0.9

06/18/09 5,833,710.0 234.2 1,840.0 288.5 24 60.00 1.136 0.005

0.6

06/18/09 5,928,841.5 234.7 1,840.0 296.4 24 60.00 1.123 0.005

0.6

06/18/09 5,948,814.1 238.3 1,840.0 294.2 24 60.00 0.757 0.004

0.7

06/18/09 5,968,522.4 240.2 1,840.0 295.2 24 60.00 0.757 0.004

0.7

06/18/09 5,954,150.2 240.3 1,840.0 294.5 24 60.00 0.883 0.004

0.8

06/18/09 5,954,359.5 239.8 1,840.0 288.0 24 60.00 0.903 0.004

06/18/09 5,901,746.0 240.4 1,840.0 295.1 24 60.00 0.998 0.005
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C 0.9

0.9

06/21/09 5,493,637.1 242.7 1,840.0 283.7 24 60.00 1.088 0.005

0.8

06/21/09 5,480,045.6 242.9 1,840.0 288.9 24 60.00 1.065 0.005

0.9

06/21/09 5,501,780.7 244.1 1,840.0 290.1 24 60.00 0.947 0.004

0.8

06/20/09 5,481,089.8 246.6 1,840.0 286.0 24 60.00 1.076 0.005

0.7

06/20/09 5,599,086.0 248.9 1,840.0 292.1 24 60.00 0.957 0.004

0.7

06/20/09 5,597,716.3 249.4 1,840.0 292.1 24 60.00 0.837 0.004

0.7

06/20/09 5,626,979.2 250.1 1,840.0 293.6 24 60.00 0.837 0.004

0.7

06/20/09 5,807,576.6 251.9 1,840.0 293.6 24 60.00 0.864 0.004

0.6

06/20/09 5,656,000.5 254.5 1,840.0 292.0 24 60.00 0.846 0.004

0.5

06/20/09 5,670,712.2 257.9 1,840.0 292.8 24 60.00 0.725 0.003

0.8

06/20/09 5,677,252.3 265.6 1,840.0 290.0 24 60.00 0.611 0.003

1.3

06/20/09 5,895,409.2 280.4 1,840.0 298.0 26 60.00 0.988 0.005

1.2

06/20/09 9,784,181.1 289.0 1,840.0 547.7 49 60.00 1.449 0.013

1.6

06/20/09 10,009,132.4 288.9 1,840.0 560.3 50 60.00 1.338 0.012

1.4

06/20/09 10,046,369.7 287.8 1,840.0 562.4 50 60.00 1.784 0.016

1.3

06/20/09 10,034,129.1 285.2 1,840.0 561.7 50 60.00 1.561 0.014

0.9

06/20/09 10,020,620.5 283.1 1,840.0 561.0 50 60.00 1.449 0.013

0.6

06/20/09 9,981,856.2 276.6 1,840.0 558.8 50 60.00 1.003 0.009

0.5

06/20/09 9,742,404.5 257.4 1,840.0 561.2 48 60.00 0.650 0.006

0.5

06/20/09 5,738,637.3 245.4 1,840.0 302.5 25 60.00 0.592 0.003

0.6

06/20/09 5,707,812.9 245.5 1,840.0 297.8 25 60.00 0.598 0.003

0.6

06/20/09 5,702,337.0 244.3 1,840.0 297.5 25 60.00 0.718 0.003

0.6

06/20/09 5,840,576.6 243.1 1,840.0 298.4 25 60.00 0.733 0.003

0.6

06/20/09 5,729,888.2 241.5 1,840.0 295.8 25 60.00 0.725 0.003

0.6

06/20/09 5,692,091.8 241.5 1,840.0 297.0 25 60.00 0.718 0.003

0.5

06/20/09 5,746,395.8 243.5 1,840.0 296.7 25 60.00 0.725 0.003

0.5

06/20/09 5,912,040.8 244.6 1,840.0 298.8 25 60.00 0.617 0.003

0.9

06/19/09 5,963,225.3 244.8 1,840.0 301.4 25 60.00 0.617 0.003

1.2

06/19/09 5,930,781.0 245.3 1,840.0 299.8 25 60.00 1.111 0.005

0.9

06/19/09 5,971,722.9 248.2 1,840.0 298.6 25 60.00 1.498 0.007

1.1

06/19/09 5,903,099.2 257.9 1,840.0 295.1 25 60.00 1.123 0.005

1.3

06/19/09 6,752,656.0 273.0 1,840.0 330.3 29 60.00 1.403 0.007

1.3

06/19/09 9,699,589.1 279.0 1,840.0 548.3 50 60.00 1.435 0.013

1.3

06/19/09 9,706,022.3 278.2 1,840.0 548.6 50 60.00 1.435 0.013

1.3

06/19/09 9,642,816.0 276.1 1,840.0 550.3 50 60.00 1.422 0.013

1.2

06/19/09 9,632,120.9 275.7 1,840.0 549.7 50 60.00 1.422 0.012

06/19/09 9,694,494.1 277.7 1,840.0 547.9 50 60.00 1.325 0.012
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00 1.2

1.3

06/22/09 10,401,954.4 289.1 1,840.0 610.6 55 60.00 1.276 0.012

1.4

06/22/09 10,392,530.0 288.4 1,840.0 610.0 55 60.00 1.382 0.013

1.3

06/22/09 10,265,320.3 286.9 1,840.0 608.1 55 60.00 1.475 0.014

1.2

06/22/09 10,436,799.7 289.5 1,840.0 612.6 55 60.00 1.382 0.014

1.2

06/22/09 10,468,526.3 290.4 1,840.0 614.5 55 60.00 1.276 0.013

1.2

06/22/09 10,454,264.0 289.1 1,840.0 613.6 55 60.00 1.276 0.013

1.2

06/22/09 10,433,582.0 286.9 1,840.0 612.4 55 60.00 1.276 0.012

1.1

06/22/09 10,421,973.8 283.9 1,840.0 617.4 55 60.00 1.264 0.012

0.8

06/22/09 10,448,786.7 281.1 1,840.0 613.3 55 60.00 1.169 0.011

0.4

06/22/09 10,622,819.4 271.3 1,840.0 629.3 56 60.00 0.843 0.008

0.7

06/22/09 7,658,957.5 246.2 1,840.0 432.9 36 60.00 0.442 0.003

0.6

06/22/09 5,679,490.5 242.4 1,840.0 299.4 25 60.00 0.829 0.004

0.6

06/22/09 5,626,665.8 243.6 1,840.0 296.6 25 60.00 0.710 0.003

0.5

06/22/09 5,661,037.9 246.2 1,840.0 295.4 25 60.00 0.718 0.003

0.5

06/22/09 5,705,104.7 247.8 1,840.0 297.7 25 60.00 0.598 0.003

0.7

06/22/09 5,787,692.8 252.1 1,840.0 298.8 25 60.00 0.604 0.003

1.0

06/21/09 5,697,609.1 263.0 1,840.0 294.2 25 60.00 0.846 0.004

0.9

06/21/09 8,124,535.1 276.2 1,840.0 415.1 38 60.00 1.221 0.008

0.9

06/21/09 9,605,872.3 278.6 1,840.0 548.2 50 60.00 0.984 0.009

0.9

06/21/09 9,629,565.0 277.8 1,840.0 549.5 50 60.00 0.984 0.009

0.8

06/21/09 9,646,279.4 275.3 1,840.0 550.5 50 60.00 0.984 0.009

0.7

06/21/09 9,617,963.2 274.8 1,840.0 554.1 50 60.00 0.867 0.008

0.2

06/21/09 9,804,278.2 266.8 1,840.0 564.8 50 60.00 0.758 0.007

0.3

06/21/09 7,770,744.7 244.4 1,840.0 439.2 38 60.00 0.221 0.002

0.3

06/21/09 5,470,067.5 240.0 1,840.0 282.4 24 60.00 0.363 0.002

0.4

06/21/09 5,453,866.4 240.9 1,840.0 281.6 24 60.00 0.363 0.002

0.5

06/21/09 5,429,406.0 241.2 1,840.0 283.3 24 60.00 0.478 0.002

0.3

06/21/09 5,463,570.6 242.0 1,840.0 282.1 24 60.00 0.604 0.003

0.5

06/21/09 5,571,938.5 244.6 1,840.0 284.7 24 60.00 0.366 0.002

0.5

06/21/09 5,655,738.6 248.1 1,840.0 298.2 25 60.00 0.592 0.003

0.5

06/21/09 5,566,997.2 248.9 1,840.0 293.5 25 60.00 0.592 0.003

0.5

06/21/09 5,638,730.2 248.6 1,840.0 297.3 25 60.00 0.592 0.003

1.0

06/21/09 5,598,917.8 247.9 1,840.0 298.2 25 60.00 0.586 0.003

1.0

06/21/09 5,611,842.5 246.6 1,840.0 298.9 25 60.00 1.172 0.006

0.9

06/21/09 5,601,474.9 245.5 1,840.0 298.3 25 60.00 1.172 0.006

1.0

06/21/09 5,622,636.7 244.7 1,840.0 299.5 25 60.00 1.054 0.005

06/21/09 5,605,014.4 243.6 1,840.0 295.5 25 60.00 1.184 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C S S SC

03:00 S S S

04:00 0.7 C

0.6

06/24/09 5,553,855.7 243.9 1,840.0 286.8 24 60.00 0.846 0.004

0.6

06/24/09 5,504,441.2 244.0 1,840.0 284.2 24 60.00 0.725 0.003

0.5

06/24/09 5,557,159.2 243.1 1,840.0 283.9 24 60.00 0.733 0.003

0.9

06/24/09 5,478,063.9 243.0 1,840.0 285.8 24 60.00 0.598 0.003

0.8

06/24/09 5,493,066.0 245.4 1,840.0 286.6 24 60.00 1.076 0.005

0.7

06/23/09 5,494,969.5 252.0 1,840.0 283.7 24 60.00 0.967 0.004

1.1

06/23/09 5,547,801.6 267.6 1,840.0 286.4 24 60.00 0.846 0.004

1.2

06/23/09 7,601,579.5 288.7 1,840.0 400.8 37 60.00 1.302 0.008

1.4

06/23/09 10,536,530.4 295.0 1,840.0 612.7 55 60.00 1.288 0.013

1.5

06/23/09 10,533,272.4 294.5 1,840.0 612.5 55 60.00 1.502 0.015

1.4

06/23/09 10,545,750.9 295.6 1,840.0 613.3 55 60.00 1.610 0.016

1.3

06/23/09 10,579,654.5 297.1 1,840.0 615.3 55 60.00 1.502 0.015

1.3

06/23/09 10,635,329.2 296.8 1,840.0 618.4 55 60.00 1.395 0.014

1.3

06/23/09 10,602,193.3 295.5 1,840.0 616.5 55 60.00 1.395 0.014

1.3

06/23/09 10,591,578.2 295.5 1,840.0 615.9 55 60.00 1.395 0.014

1.2

06/23/09 10,608,631.7 295.8 1,840.0 616.9 55 60.00 1.395 0.014

1.2

06/23/09 10,602,422.3 294.8 1,840.0 616.5 55 60.00 1.288 0.013

1.3

06/23/09 10,573,505.3 294.0 1,840.0 620.6 55 60.00 1.276 0.013

1.2

06/23/09 10,548,124.7 294.3 1,840.0 619.1 55 60.00 1.382 0.014

1.2

06/23/09 10,551,429.7 292.9 1,840.0 619.3 55 60.00 1.276 0.013

1.1

06/23/09 10,551,860.4 288.6 1,840.0 619.4 55 60.00 1.276 0.013

0.6

06/23/09 10,582,870.0 277.1 1,840.0 621.2 55 60.00 1.169 0.012

0.6

06/23/09 8,348,876.2 252.6 1,840.0 471.9 41 60.00 0.662 0.005

0.3

06/23/09 6,249,318.9 246.9 1,840.0 332.8 28 60.00 0.703 0.004

0.4

06/23/09 6,189,197.7 245.2 1,840.0 329.6 28 60.00 0.351 0.002

0.6

06/23/09 5,678,090.1 245.8 1,840.0 296.2 25 60.00 0.478 0.002

0.6

06/23/09 5,753,265.6 253.5 1,840.0 293.9 25 60.00 0.733 0.003

0.9

06/23/09 5,706,611.3 264.7 1,840.0 294.7 25 60.00 0.725 0.003

1.4

06/23/09 6,909,891.7 281.5 1,840.0 360.5 33 60.00 1.076 0.006

1.4

06/22/09 10,554,145.3 288.6 1,840.0 613.7 55 60.00 1.502 0.015

1.4

06/22/09 10,556,963.1 289.8 1,840.0 613.9 55 60.00 1.502 0.015

1.4

06/22/09 10,580,312.1 292.0 1,840.0 615.3 55 60.00 1.502 0.015

1.4

06/22/09 10,578,531.6 292.7 1,840.0 615.2 55 60.00 1.502 0.015

1.5

06/22/09 10,565,766.3 291.6 1,840.0 620.2 55 60.00 1.488 0.015

1.4

06/22/09 10,522,979.5 289.1 1,840.0 617.7 55 60.00 1.595 0.016

1.2

06/22/09 10,374,274.6 286.7 1,840.0 608.9 55 60.00 1.488 0.014

06/22/09 10,355,445.0 288.2 1,840.0 607.8 55 60.00 1.276 0.012
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00 2.1

2.1

06/25/09 10,580,843.0 291.9 1,840.0 615.3 55 60.00 2.253 0.022

1.9

06/25/09 10,567,766.7 292.1 1,840.0 614.6 55 60.00 2.253 0.022

2.0

06/25/09 10,526,404.4 292.1 1,840.0 612.1 55 60.00 2.039 0.020

2.1

06/25/09 10,535,668.8 291.5 1,840.0 612.7 55 60.00 2.146 0.021

2.1

06/25/09 10,520,958.4 290.4 1,840.0 611.8 55 60.00 2.253 0.022

2.2

06/25/09 10,530,755.5 291.0 1,840.0 612.4 55 60.00 2.253 0.022

2.2

06/25/09 10,493,181.0 290.4 1,840.0 615.9 55 60.00 2.339 0.023

2.1

06/25/09 10,502,019.3 287.8 1,840.0 610.7 55 60.00 2.361 0.023

1.6

06/25/09 10,536,782.4 282.0 1,840.0 612.7 55 60.00 2.253 0.022

0.8

06/25/09 10,379,402.0 269.0 1,840.0 597.9 53 60.00 1.733 0.017

0.9

06/25/09 7,396,102.5 249.4 1,840.0 406.0 35 60.00 0.909 0.006

0.7

06/25/09 5,625,876.2 248.3 1,840.0 290.5 24 60.00 1.088 0.005

1.2

06/25/09 5,598,428.5 250.4 1,840.0 289.0 24 60.00 0.846 0.004

1.3

06/25/09 5,616,056.5 257.8 1,840.0 286.9 24 60.00 1.466 0.007

2.0

06/25/09 5,594,071.5 273.0 1,840.0 285.8 24 60.00 1.588 0.007

2.2

06/25/09 8,056,841.2 289.5 1,840.0 420.4 41 60.00 2.392 0.016

2.2

06/25/09 10,546,054.6 292.4 1,840.0 607.5 55 60.00 2.383 0.023

1.9

06/25/09 10,583,085.4 293.4 1,840.0 609.7 55 60.00 2.383 0.023

2.1

06/24/09 10,608,948.3 294.6 1,840.0 616.9 55 60.00 2.039 0.020

2.3

06/24/09 10,611,446.8 294.2 1,840.0 611.3 55 60.00 2.275 0.022

2.4

06/24/09 10,584,561.5 293.2 1,840.0 609.8 55 60.00 2.491 0.024

2.4

06/24/09 10,587,408.4 293.5 1,840.0 609.9 55 60.00 2.600 0.025

2.3

06/24/09 10,583,484.7 294.1 1,840.0 609.7 55 60.00 2.600 0.025

2.2

06/24/09 10,560,606.5 294.6 1,840.0 614.1 55 60.00 2.468 0.024

2.3

06/24/09 10,570,313.1 293.8 1,840.0 614.7 55 60.00 2.361 0.023

2.1

06/24/09 10,552,056.9 291.9 1,840.0 607.9 55 60.00 2.491 0.024

2.1

06/24/09 10,564,689.4 293.3 1,840.0 608.6 55 60.00 2.275 0.022

1.9

06/24/09 10,560,480.9 294.1 1,840.0 614.1 55 60.00 2.253 0.022

1.9

06/24/09 10,581,024.4 294.8 1,840.0 609.6 55 60.00 2.058 0.020

2.1

06/24/09 10,589,393.2 293.9 1,840.0 615.8 55 60.00 2.039 0.020

2.1

06/24/09 10,587,108.7 291.4 1,840.0 615.7 55 60.00 2.253 0.022

2.2

06/24/09 10,544,163.3 290.1 1,840.0 613.2 55 60.00 2.253 0.022

2.1

06/24/09 10,579,510.7 290.5 1,840.0 615.3 55 60.00 2.361 0.023

1.9

06/24/09 10,534,678.7 290.0 1,840.0 612.6 55 60.00 2.253 0.022

1.3

06/24/09 10,578,215.5 285.8 1,840.0 615.1 55 60.00 2.039 0.020

0.8

06/24/09 10,666,071.4 271.8 1,840.0 620.3 55 60.00 1.395 0.014

06/24/09 7,569,204.0 245.0 1,840.0 415.5 35 60.00 0.909 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00 0.9

0.8

06/27/09 5,685,884.5 237.0 1,840.0 290.5 24 60.00 1.099 0.005

1.0

06/27/09 5,663,384.5 238.1 1,840.0 286.2 24 60.00 0.988 0.005

0.8

06/27/09 5,638,698.4 239.3 1,840.0 288.1 24 60.00 1.221 0.006

0.7

06/27/09 5,661,023.4 239.6 1,840.0 286.1 24 60.00 0.988 0.005

1.3

06/27/09 5,653,670.7 239.9 1,840.0 276.6 24 60.00 0.893 0.004

1.6

06/27/09 5,675,009.9 242.2 1,840.0 286.8 24 60.00 1.605 0.007

1.7

06/27/09 5,694,366.9 249.1 1,840.0 287.8 24 60.00 1.975 0.009

1.9

06/26/09 5,773,937.2 265.2 1,840.0 288.7 24 60.00 2.122 0.010

1.9

06/26/09 8,271,251.9 286.9 1,840.0 431.5 40 60.00 2.272 0.016

1.9

06/26/09 10,570,641.9 292.8 1,840.0 614.7 55 60.00 2.039 0.020

2.0

06/26/09 10,538,021.9 292.9 1,840.0 618.5 55 60.00 2.020 0.020

1.9

06/26/09 10,573,842.6 293.4 1,840.0 620.6 55 60.00 2.126 0.021

2.0

06/26/09 10,679,348.0 297.0 1,840.0 632.6 56 60.00 2.001 0.020

2.0

06/26/09 10,970,334.5 298.0 1,840.0 649.9 57 60.00 2.107 0.022

2.1

06/26/09 11,047,390.4 298.9 1,840.0 654.4 58 60.00 2.107 0.022

2.0

06/26/09 11,390,149.8 301.1 1,840.0 674.7 60 60.00 2.212 0.024

2.1

06/26/09 11,438,448.6 301.5 1,840.0 677.6 60 60.00 2.107 0.023

2.4

06/26/09 11,462,515.4 299.9 1,840.0 679.1 60 60.00 2.212 0.024

2.5

06/26/09 11,439,053.4 297.4 1,840.0 677.6 60 60.00 2.528 0.027

2.5

06/26/09 11,466,066.9 297.7 1,840.0 679.2 60 60.00 2.633 0.029

2.5

06/26/09 11,435,833.8 297.4 1,840.0 683.7 60 60.00 2.609 0.029

2.0

06/26/09 11,281,529.3 293.8 1,840.0 668.3 59 60.00 2.633 0.028

1.9

06/26/09 11,107,163.3 285.6 1,840.0 639.9 58 60.00 2.166 0.022

1.4

06/26/09 10,025,585.5 277.2 1,840.0 572.1 51 60.00 2.078 0.019

0.6

06/26/09 9,949,452.4 266.3 1,840.0 562.3 50 60.00 1.546 0.014

0.7

06/26/09 7,604,479.5 244.0 1,840.0 421.5 36 60.00 0.675 0.005

0.7

06/26/09 5,533,282.0 243.5 1,840.0 288.7 24 60.00 0.837 0.004

0.7

06/26/09 5,498,620.0 245.4 1,840.0 286.9 24 60.00 0.837 0.004

0.7

06/26/09 5,505,766.7 247.1 1,840.0 278.3 24 60.00 0.864 0.004

0.9

06/26/09 5,531,094.3 249.9 1,840.0 285.6 24 60.00 0.846 0.004

1.3

06/26/09 5,448,820.5 257.1 1,840.0 281.3 24 60.00 1.088 0.005

2.0

06/25/09 5,558,317.5 271.2 1,840.0 283.9 24 60.00 1.588 0.007

2.4

06/25/09 7,567,329.2 288.7 1,840.0 398.9 37 60.00 2.367 0.015

2.2

06/25/09 10,597,451.1 292.1 1,840.0 610.5 55 60.00 2.600 0.025

2.1

06/25/09 10,614,018.9 292.5 1,840.0 611.5 55 60.00 2.383 0.023

2.0

06/25/09 10,591,220.2 293.1 1,840.0 615.9 55 60.00 2.253 0.022

06/25/09 10,552,863.6 293.0 1,840.0 607.9 55 60.00 2.166 0.021
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00 1.7

1.9

06/28/09 9,154,986.1 278.3 1,840.0 512.5 45 60.00 1.895 0.016

1.8

06/28/09 9,102,774.3 278.6 1,840.0 509.6 45 60.00 2.118 0.017

1.9

06/28/09 9,132,675.8 277.8 1,840.0 511.2 45 60.00 2.006 0.016

1.9

06/28/09 9,129,000.9 278.5 1,840.0 516.0 45 60.00 2.098 0.017

1.9

06/28/09 9,203,484.4 279.1 1,840.0 515.2 45 60.00 2.118 0.017

1.7

06/28/09 9,091,931.6 279.2 1,840.0 509.0 44 60.00 2.118 0.017

1.8

06/28/09 9,486,497.3 281.8 1,840.0 536.2 47 60.00 1.877 0.016

1.8

06/28/09 10,008,645.3 282.2 1,840.0 576.6 51 60.00 1.950 0.018

1.6

06/28/09 9,948,956.7 278.4 1,840.0 567.7 51 60.00 1.968 0.018

1.1

06/28/09 9,759,100.3 269.8 1,840.0 556.9 49 60.00 1.750 0.016

1.0

06/28/09 8,697,777.6 248.8 1,840.0 486.9 43 60.00 1.226 0.010

0.9

06/28/09 5,839,887.0 241.3 1,840.0 307.9 26 60.00 1.184 0.006

0.8

06/28/09 5,565,063.2 240.2 1,840.0 290.3 24 60.00 1.076 0.005

0.8

06/28/09 5,555,498.3 240.5 1,840.0 289.8 24 60.00 0.957 0.004

0.7

06/28/09 5,569,315.9 242.3 1,840.0 290.6 24 60.00 0.957 0.004

0.9

06/28/09 5,609,978.7 242.6 1,840.0 289.6 24 60.00 0.846 0.004

0.9

06/28/09 5,551,011.1 242.9 1,840.0 283.6 24 60.00 1.099 0.005

1.2

06/28/09 5,496,185.1 243.8 1,840.0 283.8 24 60.00 1.088 0.005

1.3

06/28/09 5,662,500.7 246.3 1,840.0 292.4 24 60.00 1.450 0.007

1.8

06/28/09 5,579,720.7 252.1 1,840.0 288.1 24 60.00 1.571 0.007

1.9

06/27/09 5,588,245.5 263.6 1,840.0 282.4 24 60.00 2.222 0.010

1.6

06/27/09 7,872,886.5 277.6 1,840.0 410.8 37 60.00 2.272 0.015

1.5

06/27/09 10,071,458.1 283.1 1,840.0 563.8 51 60.00 1.784 0.016

1.7

06/27/09 10,088,087.9 284.7 1,840.0 570.2 51 60.00 1.656 0.015

1.7

06/27/09 9,982,101.2 284.7 1,840.0 564.2 51 60.00 1.877 0.017

1.8

06/27/09 10,016,298.3 284.1 1,840.0 566.1 51 60.00 1.877 0.017

1.7

06/27/09 10,027,330.1 283.6 1,840.0 561.3 51 60.00 2.006 0.018

1.7

06/27/09 10,158,176.8 287.7 1,840.0 579.7 52 60.00 1.859 0.017

1.6

06/27/09 10,540,743.6 290.3 1,840.0 613.0 55 60.00 1.824 0.018

1.9

06/27/09 10,613,549.6 290.6 1,840.0 617.2 55 60.00 1.717 0.017

1.6

06/27/09 10,617,128.1 289.7 1,840.0 617.4 55 60.00 2.039 0.020

1.5

06/27/09 10,685,688.5 290.4 1,840.0 615.6 55 60.00 1.733 0.017

1.4

06/27/09 10,734,469.7 289.8 1,840.0 624.2 55 60.00 1.610 0.016

1.4

06/27/09 10,709,550.4 284.6 1,840.0 617.0 54 60.00 1.516 0.015

1.2

06/27/09 10,249,882.2 271.8 1,840.0 590.5 52 60.00 1.516 0.014

1.1

06/27/09 9,097,282.6 249.0 1,840.0 519.1 44 60.00 1.312 0.011

06/27/09 5,768,853.6 237.6 1,840.0 297.9 25 60.00 1.329 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00 S S S

20:00 S S S

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00 0.9

0.7

06/30/09 10,099,058.8 253.7 1,840.0 603.7 52 60.00 0.939 0.009

0.7

06/30/09 5,684,114.5 239.1 1,840.0 302.7 25 60.00 0.820 0.004

0.7

06/30/09 5,594,281.7 239.3 1,840.0 294.9 24 60.00 0.829 0.004

0.8

06/30/09 5,549,461.0 240.9 1,840.0 292.5 24 60.00 0.829 0.004

0.9

06/30/09 5,543,448.7 242.1 1,840.0 292.2 24 60.00 0.947 0.004

0.9

06/30/09 5,617,228.0 242.2 1,840.0 293.1 24 60.00 1.076 0.005

1.1

06/30/09 5,593,204.6 241.5 1,840.0 291.8 24 60.00 1.076 0.005

1.1

06/30/09 5,566,337.9 240.9 1,840.0 293.4 24 60.00 1.302 0.006

1.1

06/30/09 5,597,815.1 241.3 1,840.0 295.1 24 60.00 1.302 0.006

1.4

06/29/09 5,628,777.7 242.8 1,840.0 293.7 24 60.00 1.316 0.006

0.9

06/29/09 5,615,641.0 246.8 1,840.0 293.0 24 60.00 1.674 0.008

1.5

06/29/09 5,614,287.9 255.0 1,840.0 289.9 24 60.00 1.088 0.005

1.5

06/29/09 5,667,839.3 268.0 1,840.0 292.6 24 60.00 1.813 0.008

2.0

06/29/09 7,504,393.4 285.2 1,840.0 395.6 36 60.00 1.776 0.011

2.2

06/29/09 10,722,378.4 290.9 1,840.0 629.3 56 60.00 2.126 0.021

2.2

06/29/09 10,704,890.2 289.2 1,840.0 634.2 56 60.00 2.317 0.023

2.2

06/29/09 10,675,346.4 289.6 1,840.0 632.4 56 60.00 2.317 0.023

2.0

06/29/09 10,770,067.0 291.4 1,840.0 632.2 56 60.00 2.339 0.024

1.9

06/29/09 10,775,450.9 291.7 1,840.0 632.4 56 60.00 2.126 0.022

2.0

06/29/09 10,790,166.5 290.0 1,840.0 633.3 57 60.00 2.020 0.020

2.0

06/29/09 10,609,800.1 286.8 1,840.0 617.0 55 60.00 2.146 0.021

1.9

06/29/09 10,538,841.9 286.4 1,840.0 612.9 55 60.00 2.146 0.021

1.7

06/29/09 10,534,555.0 285.3 1,840.0 612.6 55 60.00 2.039 0.020

1.0

06/29/09 10,547,427.7 279.1 1,840.0 613.3 55 60.00 1.824 0.018

1.3

06/29/09 10,093,028.2 254.4 1,840.0 586.9 51 60.00 1.073 0.010

1.1

06/29/09 5,494,707.1 237.6 1,840.0 295.7 25 60.00 1.508 0.007

0.8

06/29/09 5,408,200.5 239.0 1,840.0 288.0 24 60.00 1.289 0.006

0.7

06/29/09 5,461,328.3 240.5 1,840.0 287.9 24 60.00 0.947 0.004

0.7

06/29/09 5,458,082.7 240.6 1,840.0 287.7 24 60.00 0.829 0.004

1.2

06/29/09 5,481,267.3 240.2 1,840.0 288.9 24 60.00 0.829 0.004

1.5

06/29/09 5,434,862.4 240.1 1,840.0 286.5 24 60.00 1.420 0.007

1.2

06/29/09 5,614,937.2 241.8 1,840.0 299.1 24 60.00 1.757 0.008

1.0

06/29/09 5,682,581.2 245.9 1,840.0 299.6 24 60.00 1.420 0.007

1.2

06/28/09 5,683,645.6 251.0 1,840.0 302.7 24 60.00 1.172 0.006

1.5

06/28/09 5,726,909.1 260.8 1,840.0 301.9 24 60.00 1.420 0.007

1.8

06/28/09 7,318,423.6 273.1 1,840.0 385.8 33 60.00 1.776 0.011

06/28/09 9,295,804.2 277.0 1,840.0 520.4 45 60.00 2.006 0.017
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00 0.0

0.1

07/01/09 4,788,180.7 232.7 1,840.0 239.4 20 60.00 0.000 0.000

0.7

07/01/09 4,534,795.7 243.6 1,840.0 221.8 19 60.00 0.128 0.000

1.1

07/01/09 5,292,856.2 258.1 1,840.0 261.8 24 60.00 0.883 0.004

0.7

07/01/09 8,726,315.3 264.8 1,840.0 474.2 42 60.00 1.263 0.010

0.7

07/01/09 7,921,376.0 245.3 1,840.0 447.7 37 60.00 0.773 0.006

0.9

07/01/09 5,867,796.9 241.6 1,840.0 315.7 26 60.00 0.812 0.004

0.7

07/01/09 5,853,800.8 243.0 1,840.0 311.8 26 60.00 1.054 0.005

0.8

07/01/09 5,822,281.8 243.9 1,840.0 316.4 26 60.00 0.804 0.004

0.7

07/01/09 5,873,581.2 243.0 1,840.0 316.0 26 60.00 0.928 0.005

0.8

07/01/09 5,831,139.1 241.3 1,840.0 313.7 26 60.00 0.812 0.004

0.9

07/01/09 5,818,527.0 239.3 1,840.0 316.3 26 60.00 0.919 0.005

0.7

07/01/09 5,795,689.4 238.7 1,840.0 315.0 26 60.00 1.033 0.005

0.6

07/01/09 5,810,685.4 239.7 1,840.0 312.7 26 60.00 0.812 0.004

0.5

07/01/09 5,810,113.0 240.1 1,840.0 312.6 26 60.00 0.696 0.003

0.4

07/01/09 5,855,020.3 239.6 1,840.0 315.0 26 60.00 0.580 0.003

0.5

07/01/09 5,862,786.6 239.4 1,840.0 312.3 26 60.00 0.469 0.002

0.4

07/01/09 5,860,229.6 240.6 1,840.0 312.1 26 60.00 0.586 0.003

0.4

07/01/09 5,865,989.6 241.3 1,840.0 312.4 26 60.00 0.469 0.002

0.4

07/01/09 5,907,835.5 241.4 1,840.0 311.5 26 60.00 0.473 0.002

0.5

07/01/09 5,933,709.4 243.0 1,840.0 309.6 26 60.00 0.478 0.002

0.5

07/01/09 5,898,650.8 245.9 1,840.0 311.0 26 60.00 0.592 0.003

0.5

07/01/09 5,913,703.9 249.0 1,840.0 311.8 26 60.00 0.592 0.003

0.7

06/30/09 5,885,401.4 255.3 1,840.0 310.2 26 60.00 0.592 0.003

1.6

06/30/09 5,819,610.2 268.1 1,840.0 303.7 26 60.00 0.837 0.004

1.5

06/30/09 9,297,138.8 277.7 1,840.0 525.5 47 60.00 1.766 0.015

1.4

06/30/09 9,812,038.8 279.8 1,840.0 559.9 50 60.00 1.640 0.015

1.3

06/30/09 9,818,854.3 280.9 1,840.0 560.3 50 60.00 1.531 0.014

1.3

06/30/09 9,817,733.2 280.4 1,840.0 560.3 50 60.00 1.422 0.013

1.4

06/30/09 9,823,080.7 278.1 1,840.0 560.6 50 60.00 1.422 0.013

1.3

06/30/09 9,752,905.4 276.9 1,840.0 561.9 50 60.00 1.516 0.014

1.3

06/30/09 9,761,108.7 278.2 1,840.0 562.3 50 60.00 1.408 0.013

1.3

06/30/09 9,789,031.7 277.9 1,840.0 563.9 50 60.00 1.408 0.013

1.6

06/30/09 9,773,520.3 278.1 1,840.0 563.1 50 60.00 1.408 0.013

1.7

06/30/09 9,942,919.1 281.3 1,840.0 578.2 51 60.00 1.717 0.016

1.7

06/30/09 10,307,038.2 282.0 1,840.0 610.6 55 60.00 1.791 0.017

1.6

06/30/09 10,299,150.0 279.8 1,840.0 610.1 55 60.00 1.791 0.017

06/30/09 10,337,376.2 273.3 1,840.0 612.4 55 60.00 1.685 0.017
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00 0.7

0.4

07/03/09 5,669,377.9 234.6 1,840.0 292.7 24 60.00 0.846 0.004

0.4

07/03/09 5,602,261.3 234.1 1,840.0 295.3 24 60.00 0.473 0.002

0.3

07/03/09 5,536,246.3 235.6 1,840.0 291.8 24 60.00 0.473 0.002

0.3

07/03/09 5,515,066.5 236.6 1,840.0 290.7 24 60.00 0.355 0.002

0.3

07/03/09 5,530,270.1 235.7 1,840.0 297.5 24 60.00 0.348 0.002

0.7

07/03/09 5,531,660.0 234.7 1,840.0 297.6 24 60.00 0.348 0.002

0.6

07/03/09 5,503,251.7 234.3 1,840.0 296.1 24 60.00 0.812 0.004

0.4

07/03/09 5,532,135.8 235.8 1,840.0 297.6 24 60.00 0.696 0.003

0.4

07/03/09 5,595,298.6 239.0 1,840.0 295.0 24 60.00 0.473 0.002

0.5

07/03/09 5,536,820.1 241.1 1,840.0 294.9 24 60.00 0.469 0.002

0.5

07/03/09 5,777,213.6 243.6 1,840.0 307.7 25 60.00 0.586 0.003

0.7

07/02/09 5,834,994.1 248.6 1,840.0 310.8 26 60.00 0.586 0.003

0.9

07/02/09 5,821,688.5 258.0 1,840.0 310.1 26 60.00 0.820 0.004

1.1

07/02/09 6,503,942.0 271.3 1,840.0 342.9 30 60.00 1.065 0.006

1.2

07/02/09 9,828,862.0 278.0 1,840.0 566.2 50 60.00 1.191 0.011

1.1

07/02/09 9,854,603.9 279.4 1,840.0 567.7 50 60.00 1.300 0.012

1.1

07/02/09 9,842,258.2 280.3 1,840.0 567.0 50 60.00 1.191 0.011

1.2

07/02/09 9,858,418.8 280.3 1,840.0 567.9 50 60.00 1.191 0.011

1.2

07/02/09 9,883,958.0 279.4 1,840.0 569.4 50 60.00 1.300 0.012

1.2

07/02/09 9,886,503.1 280.1 1,840.0 569.6 50 60.00 1.300 0.012

1.2

07/02/09 9,878,826.3 280.6 1,840.0 569.1 50 60.00 1.300 0.012

1.4

07/02/09 9,881,835.8 278.8 1,840.0 569.3 50 60.00 1.300 0.012

1.6

07/02/09 9,705,465.6 276.2 1,840.0 559.1 50 60.00 1.516 0.014

1.7

07/02/09 9,667,576.8 274.0 1,840.0 562.2 50 60.00 1.717 0.015

1.4

07/02/09 9,665,543.3 272.5 1,840.0 567.4 50 60.00 1.807 0.016

1.2

07/02/09 9,666,965.8 272.9 1,840.0 562.2 50 60.00 1.502 0.014

1.0

07/02/09 9,665,150.1 271.0 1,840.0 567.3 50 60.00 1.276 0.012

0.5

07/02/09 9,677,419.3 262.8 1,840.0 568.0 50 60.00 1.063 0.010

0.5

07/02/09 8,681,837.5 241.4 1,840.0 504.9 44 60.00 0.537 0.004

0.3

07/02/09 5,818,972.4 234.3 1,840.0 319.4 26 60.00 0.568 0.003

0.3

07/02/09 5,476,282.0 233.7 1,840.0 297.6 25 60.00 0.344 0.002

0.3

07/02/09 5,529,986.8 233.1 1,840.0 297.5 25 60.00 0.348 0.002

0.4

07/02/09 5,487,518.9 233.2 1,840.0 295.3 25 60.00 0.348 0.002

0.2

07/02/09 5,442,604.4 232.7 1,840.0 295.8 25 60.00 0.459 0.002

0.2

07/02/09 5,505,191.2 230.6 1,840.0 299.2 25 60.00 0.230 0.001

0.2

07/01/09 5,489,135.8 227.6 1,840.0 298.3 25 60.00 0.230 0.001

07/01/09 5,017,128.1 227.3 1,840.0 267.2 22 60.00 0.234 0.001
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00 0.7

0.8

07/04/09 5,567,462.7 238.8 1,840.0 290.5 24 60.00 0.837 0.004

0.9

07/04/09 5,567,972.5 243.6 1,840.0 287.5 24 60.00 0.967 0.004

1.1

07/04/09 5,603,941.4 252.2 1,840.0 289.3 24 60.00 1.088 0.005

1.3

07/04/09 5,945,861.8 266.9 1,840.0 303.8 26 60.00 1.344 0.007

1.2

07/04/09 9,609,772.2 275.3 1,840.0 548.4 49 60.00 1.422 0.012

1.1

07/04/09 9,725,354.5 275.1 1,840.0 560.2 50 60.00 1.300 0.012

0.7

07/04/09 9,803,678.5 270.1 1,840.0 564.8 50 60.00 1.191 0.011

0.8

07/04/09 9,780,639.3 254.4 1,840.0 568.8 50 60.00 0.751 0.007

0.9

07/04/09 6,578,920.6 231.8 1,840.0 368.3 31 60.00 0.892 0.005

0.7

07/04/09 5,394,190.1 231.6 1,840.0 293.2 24 60.00 1.033 0.005

0.6

07/04/09 5,416,887.6 233.4 1,840.0 294.4 24 60.00 0.804 0.004

0.6

07/04/09 5,393,158.9 233.6 1,840.0 293.1 24 60.00 0.689 0.003

0.7

07/04/09 5,435,846.1 232.8 1,840.0 295.4 24 60.00 0.689 0.003

0.9

07/04/09 5,393,632.6 231.8 1,840.0 293.2 24 60.00 0.804 0.004

0.7

07/04/09 5,366,536.4 232.4 1,840.0 294.6 24 60.00 1.023 0.005

0.7

07/04/09 5,371,819.5 233.2 1,840.0 294.9 24 60.00 0.796 0.004

0.5

07/04/09 5,351,067.8 232.8 1,840.0 290.8 24 60.00 0.804 0.004

0.5

07/04/09 5,329,128.5 232.4 1,840.0 289.6 24 60.00 0.574 0.003

0.3

07/04/09 5,398,727.1 233.1 1,840.0 293.4 24 60.00 0.574 0.003

0.5

07/04/09 5,309,974.6 233.4 1,840.0 288.6 24 60.00 0.344 0.002

0.5

07/04/09 5,351,363.2 232.7 1,840.0 287.9 24 60.00 0.580 0.003

0.7

07/04/09 5,271,546.7 230.9 1,840.0 280.8 24 60.00 0.586 0.003

0.5

07/04/09 5,296,882.8 229.4 1,840.0 287.9 24 60.00 0.804 0.004

0.4

07/04/09 5,290,850.9 230.0 1,840.0 284.7 24 60.00 0.580 0.003

0.3

07/03/09 5,280,345.5 232.2 1,840.0 284.1 24 60.00 0.464 0.002

0.3

07/03/09 5,270,823.0 232.6 1,840.0 283.6 24 60.00 0.348 0.002

0.4

07/03/09 5,297,350.1 231.9 1,840.0 285.0 24 60.00 0.348 0.002

0.6

07/03/09 5,303,270.2 230.7 1,840.0 285.3 24 60.00 0.464 0.002

0.7

07/03/09 5,278,295.9 230.3 1,840.0 284.0 24 60.00 0.696 0.003

0.9

07/03/09 5,261,071.5 231.0 1,840.0 283.1 24 60.00 0.812 0.004

0.8

07/03/09 5,290,242.7 232.1 1,840.0 290.4 24 60.00 1.023 0.005

0.8

07/03/09 5,306,371.0 235.0 1,840.0 282.6 23 60.00 0.937 0.004

1.4

07/03/09 5,495,477.7 236.6 1,840.0 295.7 24 60.00 0.928 0.004

1.2

07/03/09 5,740,513.9 235.7 1,840.0 296.4 24 60.00 1.692 0.008

1.3

07/03/09 5,973,426.9 235.0 1,840.0 298.6 24 60.00 1.498 0.007

0.9

07/03/09 5,927,363.0 235.3 1,840.0 296.3 24 60.00 1.622 0.008

07/03/09 5,778,861.9 235.4 1,840.0 295.2 24 60.00 1.099 0.005
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00 1.5

1.4

07/06/09 10,177,100.6 286.2 1,840.0 586.3 50 60.00 1.625 0.015

1.7

07/06/09 10,308,502.1 285.7 1,840.0 588.3 50 60.00 1.531 0.014

1.5

07/06/09 9,834,506.8 279.7 1,840.0 571.9 50 60.00 1.824 0.017

1.3

07/06/09 9,595,572.5 278.1 1,840.0 558.0 50 60.00 1.610 0.014

1.3

07/06/09 9,775,987.4 277.7 1,840.0 557.9 50 60.00 1.422 0.013

0.9

07/06/09 9,797,405.3 274.1 1,840.0 559.1 50 60.00 1.422 0.013

0.4

07/06/09 9,960,912.8 260.6 1,840.0 568.4 51 60.00 0.984 0.009

0.4

07/06/09 7,194,120.8 234.1 1,840.0 398.8 34 60.00 0.450 0.003

0.5

07/06/09 5,074,161.7 233.7 1,840.0 264.7 22 60.00 0.478 0.002

0.5

07/06/09 5,128,885.8 235.2 1,840.0 264.8 22 60.00 0.604 0.003

0.5

07/06/09 5,159,650.0 235.2 1,840.0 263.6 22 60.00 0.611 0.003

0.9

07/06/09 5,073,751.1 237.9 1,840.0 250.9 21 60.00 0.631 0.003

1.0

07/06/09 5,146,664.3 244.8 1,840.0 265.7 22 60.00 1.088 0.005

1.1

07/05/09 5,355,204.3 255.6 1,840.0 288.1 24 60.00 1.160 0.005

1.4

07/05/09 5,836,684.5 272.6 1,840.0 304.5 27 60.00 1.316 0.006

1.4

07/05/09 9,634,628.5 281.6 1,840.0 549.8 49 60.00 1.531 0.013

1.4

07/05/09 9,743,805.6 281.4 1,840.0 561.3 50 60.00 1.516 0.014

1.4

07/05/09 9,727,693.1 279.9 1,840.0 560.4 50 60.00 1.516 0.014

1.2

07/05/09 9,744,286.6 278.3 1,840.0 561.3 50 60.00 1.516 0.014

0.5

07/05/09 9,785,471.6 271.0 1,840.0 563.7 50 60.00 1.300 0.012

0.5

07/05/09 8,735,417.0 247.4 1,840.0 498.5 43 60.00 0.547 0.004

0.6

07/05/09 5,416,548.4 239.0 1,840.0 288.5 24 60.00 0.586 0.003

0.7

07/05/09 5,473,119.7 239.8 1,840.0 291.5 24 60.00 0.703 0.003

0.6

07/05/09 5,473,604.1 239.2 1,840.0 291.6 24 60.00 0.820 0.004

0.7

07/05/09 5,495,534.9 237.8 1,840.0 292.7 24 60.00 0.703 0.003

0.8

07/05/09 5,474,863.0 236.4 1,840.0 291.6 24 60.00 0.820 0.004

0.6

07/05/09 5,499,225.1 236.5 1,840.0 292.9 24 60.00 0.937 0.004

0.6

07/05/09 5,491,285.3 237.3 1,840.0 292.5 24 60.00 0.703 0.003

0.5

07/05/09 5,476,430.7 236.5 1,840.0 291.7 24 60.00 0.703 0.003

0.6

07/05/09 5,461,385.5 235.4 1,840.0 290.9 24 60.00 0.586 0.003

0.7

07/05/09 5,417,596.5 234.9 1,840.0 288.6 24 60.00 0.703 0.003

1.0

07/05/09 5,503,713.0 235.0 1,840.0 290.2 24 60.00 0.829 0.004

0.8

07/05/09 5,599,629.8 235.1 1,840.0 292.2 24 60.00 1.196 0.006

0.8

07/05/09 5,632,314.4 235.0 1,840.0 290.8 24 60.00 0.967 0.004

0.9

07/05/09 5,579,852.8 236.1 1,840.0 285.1 24 60.00 0.977 0.004

0.9

07/05/09 5,585,989.5 236.5 1,840.0 291.4 24 60.00 1.076 0.005

07/05/09 5,628,909.7 236.6 1,840.0 293.7 24 60.00 1.076 0.005
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 0.4 C

0.7

07/08/09 5,225,950.5 248.9 1,840.0 264.1 22 60.00 0.494 0.002

1.4

07/08/09 5,219,127.8 262.6 1,840.0 266.6 22 60.00 0.855 0.004

1.6

07/07/09 7,715,850.1 276.8 1,840.0 411.0 38 60.00 1.640 0.011

1.5

07/07/09 9,936,023.9 279.1 1,840.0 594.0 53 60.00 1.670 0.016

1.3

07/07/09 9,947,516.0 280.4 1,840.0 594.7 53 60.00 1.566 0.015

1.4

07/07/09 9,959,539.3 282.7 1,840.0 595.4 53 60.00 1.357 0.013

1.4

07/07/09 9,980,648.7 283.1 1,840.0 596.7 53 60.00 1.461 0.014

1.5

07/07/09 9,952,963.0 282.2 1,840.0 589.6 53 60.00 1.475 0.014

1.4

07/07/09 9,967,979.8 280.5 1,840.0 590.5 53 60.00 1.580 0.015

1.3

07/07/09 9,982,278.4 280.4 1,840.0 591.3 53 60.00 1.475 0.014

1.2

07/07/09 10,000,912.6 282.2 1,840.0 592.5 53 60.00 1.369 0.013

1.1

07/07/09 10,030,887.8 282.7 1,840.0 594.2 53 60.00 1.264 0.012

1.2

07/07/09 10,057,645.5 282.1 1,840.0 595.8 53 60.00 1.159 0.011

1.3

07/07/09 10,056,169.3 281.2 1,840.0 590.2 53 60.00 1.276 0.012

1.3

07/07/09 10,050,673.7 280.1 1,840.0 590.0 53 60.00 1.382 0.013

1.3

07/07/09 10,004,815.7 281.2 1,840.0 587.3 53 60.00 1.382 0.013

1.4

07/07/09 10,035,347.8 280.3 1,840.0 589.0 53 60.00 1.382 0.013

1.3

07/07/09 9,721,565.2 277.0 1,840.0 560.1 50 60.00 1.516 0.014

1.1

07/07/09 9,753,544.9 273.2 1,840.0 561.9 50 60.00 1.408 0.013

0.7

07/07/09 9,749,951.4 268.7 1,840.0 556.4 50 60.00 1.203 0.011

0.2

07/07/09 9,231,332.7 248.6 1,840.0 526.8 46 60.00 0.765 0.006

0.5

07/07/09 5,278,643.0 237.4 1,840.0 284.0 24 60.00 0.232 0.001

0.7

07/07/09 5,222,062.5 239.7 1,840.0 278.1 24 60.00 0.586 0.003

1.0

07/07/09 5,216,603.2 246.6 1,840.0 275.0 24 60.00 0.829 0.004

1.5

07/07/09 5,205,534.8 258.6 1,840.0 274.4 24 60.00 1.184 0.005

1.3

07/07/09 7,486,573.0 275.1 1,840.0 386.6 36 60.00 1.813 0.011

1.3

07/06/09 9,839,034.1 282.0 1,840.0 577.5 53 60.00 1.382 0.013

1.3

07/06/09 9,864,732.7 283.3 1,840.0 579.0 53 60.00 1.382 0.013

1.5

07/06/09 9,859,777.1 283.6 1,840.0 578.7 52 60.00 1.382 0.013

1.5

07/06/09 9,809,417.9 283.8 1,840.0 575.7 52 60.00 1.595 0.015

1.4

07/06/09 9,810,740.8 285.0 1,840.0 581.2 53 60.00 1.580 0.015

0.4

07/06/09 9,777,526.3 286.5 1,840.0 579.2 52 60.00 1.475 0.014

1.6

07/06/09 9,820,923.5 287.6 1,840.0 576.5 53 60.00 0.425 0.004

1.6

07/06/09 10,314,712.1 290.5 1,840.0 616.7 54 60.00 1.670 0.016

1.5

07/06/09 10,537,433.4 289.5 1,840.0 624.2 53 60.00 1.685 0.017

1.5

07/06/09 10,214,578.4 288.6 1,840.0 588.5 50 60.00 1.625 0.015

07/06/09 10,215,718.9 287.5 1,840.0 583.0 50 60.00 1.640 0.015
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

02:00 C S S SC

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00 S S S

08:00 M

09:00

10:00

11:00

12:00

13:00

14:00 1.8

1.5

07/09/09 9,599,149.8 276.7 1,840.0 558.2 50 60.00 1.931 0.017

1.6

07/09/09 9,628,600.8 277.9 1,840.0 559.9 50 60.00 1.610 0.014

1.4

07/09/09 9,605,058.4 276.9 1,840.0 563.8 50 60.00 1.701 0.015

1.6

07/09/09 9,780,482.5 274.7 1,840.0 558.1 50 60.00 1.531 0.014

1.4

07/09/09 9,555,135.4 272.4 1,840.0 545.3 50 60.00 1.750 0.015

1.1

07/09/09 9,534,002.4 272.7 1,840.0 544.1 50 60.00 1.531 0.013

1.1

07/09/09 9,569,012.4 270.9 1,840.0 551.3 50 60.00 1.191 0.011

1.0

07/09/09 9,516,879.4 267.5 1,840.0 548.3 50 60.00 1.191 0.010

0.5

07/09/09 9,609,196.4 253.3 1,840.0 564.0 50 60.00 1.063 0.010

0.6

07/09/09 6,430,162.2 232.8 1,840.0 356.4 30 60.00 0.563 0.003

0.5

07/09/09 5,186,563.0 232.3 1,840.0 273.4 23 60.00 0.710 0.003

0.5

07/09/09 5,214,052.8 232.9 1,840.0 274.9 23 60.00 0.592 0.003

1.0

07/09/09 5,186,339.8 235.1 1,840.0 264.9 23 60.00 0.611 0.003

1.0

07/09/09 5,142,091.9 240.6 1,840.0 257.1 22 60.00 1.248 0.005

1.4

07/09/09 5,151,199.8 251.7 1,840.0 246.4 20 60.00 1.305 0.005

1.5

07/08/09 6,087,754.0 266.3 1,840.0 311.0 27 60.00 1.710 0.009

1.5

07/08/09 9,024,312.4 271.0 1,840.0 515.0 45 60.00 1.640 0.014

1.5

07/08/09 9,012,740.9 270.7 1,840.0 514.3 45 60.00 1.640 0.013

1.4

07/08/09 9,038,064.3 271.6 1,840.0 515.8 45 60.00 1.640 0.014

1.4

07/08/09 9,020,967.9 272.3 1,840.0 514.8 45 60.00 1.531 0.013

1.4

07/08/09 8,985,843.7 272.0 1,840.0 512.8 45 60.00 1.531 0.013

1.4

07/08/09 9,015,153.5 272.8 1,840.0 514.4 45 60.00 1.531 0.013

1.4

07/08/09 9,192,267.6 277.2 1,840.0 524.5 46 60.00 1.531 0.013

1.4

07/08/09 9,719,735.6 278.3 1,840.0 565.2 50 60.00 1.502 0.014

1.4

07/08/09 9,675,046.2 277.0 1,840.0 562.6 49 60.00 1.502 0.014

1.2

07/08/09 9,733,114.0 277.5 1,840.0 566.0 50 60.00 1.502 0.014

1.3

07/08/09 9,740,006.6 277.5 1,840.0 566.4 50 60.00 1.288 0.012

1.3

07/08/09 9,706,238.0 275.8 1,840.0 564.4 50 60.00 1.395 0.013

1.3

07/08/09 9,719,042.2 275.4 1,840.0 565.2 50 60.00 1.395 0.013

1.2

07/08/09 9,688,152.9 275.9 1,840.0 563.4 50 60.00 1.395 0.013

1.2

07/08/09 9,719,735.2 274.4 1,840.0 565.2 50 60.00 1.288 0.012

1.1

07/08/09 9,660,517.9 270.2 1,840.0 561.8 50 60.00 1.288 0.012

0.7

07/08/09 9,645,444.3 260.1 1,840.0 566.1 50 60.00 1.169 0.011

0.5

07/08/09 7,584,824.3 237.4 1,840.0 428.7 37 60.00 0.773 0.005

0.5

07/08/09 5,228,305.9 233.9 1,840.0 267.1 22 60.00 0.611 0.003

0.5

07/08/09 5,251,868.6 236.4 1,840.0 262.6 22 60.00 0.624 0.003

07/08/09 5,173,556.8 241.8 1,840.0 261.5 22 60.00 0.617 0.003
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00 0.8

0.7

07/11/09 5,338,333.2 238.2 1,840.0 287.2 24 60.00 0.928 0.004

0.7

07/11/09 5,349,980.5 243.4 1,840.0 284.9 24 60.00 0.820 0.004

0.8

07/11/09 5,446,448.3 248.5 1,840.0 290.1 24 60.00 0.820 0.004

1.6

07/11/09 5,430,613.3 257.3 1,840.0 286.3 24 60.00 0.947 0.004

2.2

07/10/09 6,175,457.8 271.5 1,840.0 318.8 28 60.00 1.934 0.010

2.1

07/10/09 9,686,106.1 279.3 1,840.0 568.5 50 60.00 2.339 0.021

2.1

07/10/09 9,678,017.1 279.8 1,840.0 573.3 50 60.00 2.212 0.020

2.2

07/10/09 9,700,059.0 278.6 1,840.0 569.3 50 60.00 2.233 0.020

2.2

07/10/09 9,685,680.1 277.1 1,840.0 568.5 50 60.00 2.339 0.021

2.0

07/10/09 9,668,788.7 277.8 1,840.0 567.5 50 60.00 2.339 0.021

2.0

07/10/09 9,698,108.2 280.6 1,840.0 574.5 50 60.00 2.107 0.019

2.1

07/10/09 9,716,697.0 281.0 1,840.0 570.3 50 60.00 2.126 0.019

2.4

07/10/09 9,729,489.9 280.0 1,840.0 576.3 50 60.00 2.212 0.020

2.1

07/10/09 9,718,013.9 277.7 1,840.0 575.7 50 60.00 2.528 0.023

14.8

07/10/09 9,718,249.0 278.6 1,840.0 565.1 50 60.00 2.253 0.020

1.6

07/10/09 9,701,082.4 277.8 1,840.0 574.7 50 60.00 15.590 0.143

1.5

07/10/09 9,904,272.2 275.3 1,840.0 559.8 50 60.00 1.766 0.016

1.7

07/10/09 9,624,196.2 272.3 1,840.0 549.2 50 60.00 1.640 0.014

1.3

07/10/09 9,490,845.8 268.1 1,840.0 541.6 50 60.00 1.859 0.016

1.1

07/10/09 9,410,224.2 267.2 1,840.0 537.0 50 60.00 1.422 0.012

1.0

07/10/09 9,388,995.4 265.9 1,840.0 535.8 50 60.00 1.203 0.010

0.5

07/10/09 9,428,871.5 253.1 1,840.0 543.2 50 60.00 1.083 0.009

1.2

07/10/09 6,556,434.8 231.6 1,840.0 356.3 30 60.00 0.574 0.003

1.1

07/10/09 5,227,959.5 229.1 1,840.0 269.9 22 60.00 1.450 0.006

1.1

07/10/09 5,211,220.8 230.4 1,840.0 269.0 22 60.00 1.329 0.006

0.9

07/10/09 5,215,676.9 234.1 1,840.0 269.3 22 60.00 1.329 0.006

1.0

07/10/09 5,255,555.5 239.8 1,840.0 268.5 22 60.00 1.099 0.005

1.4

07/10/09 5,309,259.3 249.1 1,840.0 268.3 22 60.00 1.235 0.005

1.8

07/09/09 5,458,345.5 263.9 1,840.0 272.9 23 60.00 1.747 0.008

1.7

07/09/09 9,177,771.6 273.4 1,840.0 543.7 48 60.00 1.896 0.016

1.6

07/09/09 9,525,005.8 274.1 1,840.0 569.4 50 60.00 1.774 0.016

1.6

07/09/09 9,565,541.4 273.1 1,840.0 566.7 50 60.00 1.685 0.015

1.6

07/09/09 9,466,478.4 272.9 1,840.0 560.8 50 60.00 1.685 0.015

1.5

07/09/09 9,449,867.4 274.4 1,840.0 559.8 50 60.00 1.685 0.015

1.6

07/09/09 9,439,287.1 277.7 1,840.0 564.3 50 60.00 1.566 0.014

1.7

07/09/09 9,579,793.5 278.9 1,840.0 562.3 50 60.00 1.701 0.015

07/09/09 9,624,410.3 277.1 1,840.0 559.7 50 60.00 1.824 0.016
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00 0.7

0.7

07/12/09 5,710,735.1 243.6 1,840.0 291.8 24 60.00 0.855 0.004

0.7

07/12/09 5,690,157.6 242.8 1,840.0 290.7 24 60.00 0.855 0.004

0.6

07/12/09 5,700,138.2 241.5 1,840.0 291.2 24 60.00 0.855 0.004

0.6

07/12/09 5,699,496.9 239.6 1,840.0 291.1 24 60.00 0.733 0.003

0.6

07/12/09 5,729,527.7 237.8 1,840.0 292.7 24 60.00 0.733 0.003

0.4

07/12/09 5,653,579.3 236.8 1,840.0 288.8 24 60.00 0.733 0.003

0.3

07/12/09 5,512,790.0 236.6 1,840.0 287.6 24 60.00 0.478 0.002

0.2

07/12/09 5,476,719.2 235.3 1,840.0 288.7 24 60.00 0.355 0.002

0.2

07/12/09 5,483,546.6 233.0 1,840.0 289.1 24 60.00 0.237 0.001

0.4

07/12/09 5,422,370.0 230.9 1,840.0 285.8 24 60.00 0.237 0.001

0.5

07/12/09 5,400,478.0 228.8 1,840.0 284.7 24 60.00 0.473 0.002

0.5

07/12/09 5,432,564.4 224.4 1,840.0 280.5 24 60.00 0.604 0.003

0.5

07/12/09 4,967,960.8 222.4 1,840.0 243.0 20 60.00 0.638 0.002

0.5

07/12/09 4,699,548.5 224.9 1,840.0 227.3 19 60.00 0.645 0.002

0.6

07/12/09 4,707,833.1 228.7 1,840.0 225.2 19 60.00 0.652 0.002

0.4

07/12/09 4,790,135.4 233.3 1,840.0 231.7 19 60.00 0.774 0.003

0.6

07/12/09 5,030,447.8 240.9 1,840.0 246.0 21 60.00 0.510 0.002

0.8

07/11/09 5,532,457.3 247.9 1,840.0 297.6 25 60.00 0.696 0.003

1.3

07/11/09 5,529,378.5 258.1 1,840.0 294.5 25 60.00 0.937 0.004

2.0

07/11/09 6,092,161.4 274.1 1,840.0 311.2 27 60.00 1.588 0.008

2.1

07/11/09 9,556,475.9 282.5 1,840.0 566.1 49 60.00 2.107 0.019

2.0

07/11/09 9,627,066.7 283.5 1,840.0 570.3 50 60.00 2.212 0.020

1.9

07/11/09 9,607,084.7 285.2 1,840.0 569.1 50 60.00 2.107 0.019

1.9

07/11/09 9,649,341.5 285.0 1,840.0 571.6 50 60.00 2.001 0.018

2.0

07/11/09 9,627,481.0 284.0 1,840.0 570.3 50 60.00 2.001 0.018

1.9

07/11/09 9,617,163.3 284.4 1,840.0 569.7 50 60.00 2.107 0.019

1.9

07/11/09 9,636,815.1 285.1 1,840.0 570.9 50 60.00 2.001 0.018

2.2

07/11/09 9,713,481.7 283.8 1,840.0 570.1 50 60.00 2.020 0.018

2.1

07/11/09 9,673,112.2 281.4 1,840.0 567.8 50 60.00 2.339 0.021

2.0

07/11/09 9,711,575.2 280.1 1,840.0 570.1 50 60.00 2.233 0.020

1.8

07/11/09 9,716,326.5 277.5 1,840.0 570.3 50 60.00 2.126 0.019

0.7

07/11/09 9,793,896.1 268.9 1,840.0 574.9 50 60.00 1.914 0.018

0.4

07/11/09 8,998,957.0 246.0 1,840.0 523.3 44 60.00 0.751 0.006

0.4

07/11/09 5,401,520.6 236.9 1,840.0 284.8 24 60.00 0.473 0.002

0.3

07/11/09 5,417,457.1 236.7 1,840.0 288.5 24 60.00 0.469 0.002

0.5

07/11/09 5,411,774.9 236.3 1,840.0 288.2 24 60.00 0.351 0.002

07/11/09 5,397,838.5 236.4 1,840.0 284.6 24 60.00 0.592 0.003
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00 S S S

20:00 S S S

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C 1.1 C

1.2

07/14/09 6,226,237.5 235.4 1,840.0 301.1 25 60.00 1.419 0.007

0.8

07/14/09 6,167,979.5 235.4 1,840.0 295.0 24 60.00 1.566 0.007

0.8

07/14/09 6,023,868.2 233.1 1,840.0 291.4 24 60.00 1.032 0.005

0.4

07/14/09 5,695,881.6 231.8 1,840.0 260.0 22 60.00 1.093 0.005

0.5

07/14/09 5,360,495.3 234.7 1,840.0 241.8 19 60.00 0.553 0.002

0.6

07/14/09 5,356,081.6 241.0 1,840.0 241.6 19 60.00 0.692 0.003

0.8

07/13/09 5,625,268.2 252.1 1,840.0 253.7 21 60.00 0.830 0.003

1.4

07/13/09 6,732,173.1 268.9 1,840.0 329.3 29 60.00 1.021 0.005

1.3

07/13/09 9,801,888.2 276.9 1,840.0 570.0 50 60.00 1.502 0.014

1.3

07/13/09 9,818,836.7 278.6 1,840.0 571.0 50 60.00 1.395 0.013

1.2

07/13/09 9,848,068.7 279.4 1,840.0 567.3 50 60.00 1.408 0.013

1.2

07/13/09 9,799,367.4 279.0 1,840.0 569.8 50 60.00 1.288 0.012

1.0

07/13/09 9,857,792.6 277.8 1,840.0 573.3 50 60.00 1.288 0.012

0.7

07/13/09 9,814,901.7 277.4 1,840.0 570.8 50 60.00 1.073 0.010

0.1

07/13/09 9,837,311.2 278.7 1,840.0 572.0 50 60.00 0.751 0.007

0.0

07/13/09 9,959,846.0 277.7 1,840.0 573.8 50 60.00 0.108 0.001

0.0

07/13/09 8,998,071.9 274.0 1,840.0 577.0 50 60.00 0.000 0.000

0.0

07/13/09 8,639,179.4 271.9 1,840.0 568.1 50 60.00 0.000 0.000

0.0

07/13/09 8,630,602.2 269.5 1,840.0 567.6 50 60.00 0.000 0.000

0.4

07/13/09 8,634,183.1 267.9 1,840.0 563.1 50 60.00 0.000 0.000

0.9

07/13/09 8,690,326.9 258.8 1,840.0 566.7 50 60.00 0.383 0.003

1.0

07/13/09 8,260,915.2 237.5 1,840.0 444.5 37 60.00 1.044 0.007

1.2

07/13/09 5,679,998.8 224.7 1,840.0 240.8 19 60.00 1.472 0.006

1.4

07/13/09 5,100,809.1 223.9 1,840.0 232.9 19 60.00 1.640 0.006

1.5

07/13/09 5,104,298.4 225.0 1,840.0 233.0 19 60.00 1.914 0.007

1.4

07/13/09 5,122,215.2 225.6 1,840.0 233.8 19 60.00 2.050 0.008

1.2

07/13/09 5,134,499.8 226.5 1,840.0 234.4 19 60.00 1.914 0.007

1.2

07/13/09 5,090,561.4 229.2 1,840.0 229.6 19 60.00 1.660 0.006

1.5

07/13/09 5,093,340.5 233.5 1,840.0 229.7 19 60.00 1.660 0.006

1.4

07/13/09 5,314,449.6 238.7 1,840.0 231.0 19 60.00 2.153 0.008

1.1

07/12/09 6,199,128.0 248.3 1,840.0 239.2 19 60.00 2.264 0.009

1.4

07/12/09 5,810,012.5 262.3 1,840.0 271.6 23 60.00 1.469 0.006

1.6

07/12/09 8,020,760.2 277.1 1,840.0 418.5 38 60.00 1.674 0.011

1.7

07/12/09 9,720,991.4 278.4 1,840.0 570.6 50 60.00 1.701 0.016

1.6

07/12/09 9,736,429.8 278.4 1,840.0 571.5 50 60.00 1.807 0.017

0.9

07/12/09 9,777,809.2 274.2 1,840.0 573.9 50 60.00 1.701 0.016

07/12/09 9,078,831.3 253.8 1,840.0 532.9 45 60.00 0.957 0.008
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00 1.7

1.8

07/15/09 9,858,629.8 287.0 1,840.0 568.0 50 60.00 1.841 0.017

1.9

07/15/09 10,095,898.5 287.9 1,840.0 592.6 52 60.00 1.914 0.018

2.1

07/15/09 10,160,789.2 289.3 1,840.0 596.4 53 60.00 2.020 0.019

1.9

07/15/09 10,205,922.2 288.5 1,840.0 593.5 53 60.00 2.253 0.021

1.7

07/15/09 10,250,101.2 284.6 1,840.0 601.6 53 60.00 2.020 0.019

1.4

07/15/09 9,579,929.9 264.4 1,840.0 551.9 47 60.00 1.841 0.016

1.6

07/15/09 6,013,248.3 259.8 1,840.0 277.8 22 60.00 1.891 0.008

1.7

07/15/09 6,830,303.6 276.6 1,840.0 326.7 29 60.00 2.088 0.011

1.6

07/15/09 10,229,859.3 283.9 1,840.0 600.5 53 60.00 1.807 0.017

1.5

07/15/09 10,210,923.5 280.7 1,840.0 599.3 53 60.00 1.701 0.016

1.6

07/15/09 10,192,717.9 277.2 1,840.0 598.3 53 60.00 1.595 0.015

1.3

07/15/09 10,139,294.5 271.3 1,840.0 595.1 53 60.00 1.701 0.016

1.3

07/15/09 10,275,198.2 256.6 1,840.0 603.1 52 60.00 1.382 0.013

1.8

07/15/09 6,914,382.4 234.0 1,840.0 364.5 30 60.00 1.539 0.009

1.6

07/15/09 5,943,871.7 233.8 1,840.0 294.0 24 60.00 2.271 0.011

1.5

07/15/09 5,887,403.7 235.0 1,840.0 291.2 24 60.00 2.019 0.009

1.4

07/15/09 5,931,235.5 235.8 1,840.0 293.3 24 60.00 1.893 0.009

1.6

07/15/09 5,927,241.8 238.0 1,840.0 293.1 24 60.00 1.766 0.008

1.8

07/15/09 6,126,727.4 241.3 1,840.0 293.0 24 60.00 2.088 0.010

1.7

07/14/09 6,349,070.7 248.2 1,840.0 293.3 24 60.00 2.431 0.011

1.7

07/14/09 6,417,159.1 259.9 1,840.0 299.9 24 60.00 2.270 0.011

1.9

07/14/09 8,253,530.6 275.1 1,840.0 417.2 37 60.00 2.099 0.014

1.8

07/14/09 9,883,751.0 277.1 1,840.0 574.8 50 60.00 2.039 0.019

1.6

07/14/09 9,885,711.6 279.1 1,840.0 574.9 50 60.00 1.931 0.018

1.6

07/14/09 9,901,626.3 279.7 1,840.0 575.8 50 60.00 1.717 0.016

1.7

07/14/09 9,880,189.8 279.3 1,840.0 574.5 50 60.00 1.717 0.016

1.6

07/14/09 9,909,994.8 277.9 1,840.0 581.7 50 60.00 1.807 0.017

1.5

07/14/09 9,885,684.5 280.1 1,840.0 580.3 50 60.00 1.701 0.016

1.5

07/14/09 9,897,177.7 282.1 1,840.0 580.9 50 60.00 1.595 0.015

1.7

07/14/09 9,931,586.4 282.1 1,840.0 583.0 50 60.00 1.595 0.015

1.8

07/14/09 9,899,385.6 280.5 1,840.0 581.0 50 60.00 1.807 0.017

1.6

07/14/09 9,767,143.0 277.3 1,840.0 573.3 50 60.00 1.914 0.018

1.8

07/14/09 9,740,985.3 274.3 1,840.0 571.8 50 60.00 1.701 0.016

1.7

07/14/09 9,746,126.8 270.4 1,840.0 572.0 50 60.00 1.914 0.018

1.4

07/14/09 9,783,616.9 264.0 1,840.0 574.3 50 60.00 1.807 0.017

1.4

07/14/09 8,574,481.2 242.3 1,840.0 484.6 41 60.00 1.546 0.012

07/14/09 6,234,485.0 235.6 1,840.0 301.5 25 60.00 1.806 0.009
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00 1.1

0.8

07/17/09 5,551,676.0 233.9 1,840.0 289.7 25 60.00 1.316 0.006

1.0

07/17/09 5,572,574.1 232.6 1,840.0 287.7 25 60.00 0.967 0.004

1.0

07/17/09 5,463,734.0 232.4 1,840.0 288.0 25 60.00 1.184 0.005

1.0

07/17/09 5,537,875.7 235.0 1,840.0 285.9 25 60.00 1.209 0.006

0.9

07/17/09 5,536,616.5 236.2 1,840.0 288.9 25 60.00 1.196 0.006

0.9

07/17/09 5,572,178.3 236.1 1,840.0 290.7 25 60.00 1.076 0.005

1.3

07/17/09 5,525,915.5 236.3 1,840.0 288.3 25 60.00 1.076 0.005

1.0

07/17/09 5,527,151.4 239.0 1,840.0 288.4 25 60.00 1.555 0.007

0.7

07/16/09 5,515,768.8 241.7 1,840.0 287.8 25 60.00 1.196 0.006

0.7

07/16/09 5,563,379.9 244.7 1,840.0 290.2 25 60.00 0.837 0.004

1.1

07/16/09 5,580,477.7 251.4 1,840.0 291.1 25 60.00 0.837 0.004

1.5

07/16/09 5,515,078.4 265.8 1,840.0 287.7 25 60.00 1.316 0.006

1.5

07/16/09 8,340,217.6 279.9 1,840.0 453.3 42 60.00 1.722 0.012

1.6

07/16/09 9,640,478.5 281.3 1,840.0 555.3 50 60.00 1.625 0.014

1.6

07/16/09 9,628,766.9 280.6 1,840.0 554.7 50 60.00 1.733 0.015

1.6

07/16/09 9,664,264.3 281.7 1,840.0 551.5 50 60.00 1.750 0.015

1.6

07/16/09 9,663,141.6 283.1 1,840.0 556.7 50 60.00 1.733 0.015

1.6

07/16/09 9,693,956.0 282.6 1,840.0 558.5 50 60.00 1.733 0.015

1.3

07/16/09 9,684,009.4 281.1 1,840.0 557.9 50 60.00 1.733 0.015

1.4

07/16/09 9,652,783.1 279.7 1,840.0 556.1 50 60.00 1.408 0.013

1.4

07/16/09 9,607,119.7 277.5 1,840.0 553.4 50 60.00 1.516 0.013

1.2

07/16/09 9,589,481.3 275.9 1,840.0 552.4 50 60.00 1.516 0.013

1.3

07/16/09 9,578,881.7 276.3 1,840.0 551.8 50 60.00 1.300 0.011

0.2

07/16/09 9,624,713.2 275.1 1,840.0 549.3 50 60.00 1.422 0.012

0.1

07/16/09 9,658,401.1 270.9 1,840.0 551.1 50 60.00 0.219 0.002

0.8

07/16/09 9,689,220.1 258.4 1,840.0 552.9 50 60.00 0.109 0.001

1.6

07/16/09 7,357,413.1 238.7 1,840.0 403.8 35 60.00 0.909 0.006

1.3

07/16/09 5,661,578.0 236.8 1,840.0 289.3 25 60.00 1.954 0.009

1.3

07/16/09 5,676,771.9 238.3 1,840.0 293.1 25 60.00 1.571 0.007

1.0

07/16/09 5,732,393.8 242.1 1,840.0 289.7 25 60.00 1.605 0.007

1.1

07/16/09 5,840,420.0 244.7 1,840.0 298.3 25 60.00 1.221 0.006

1.9

07/16/09 5,813,326.9 248.9 1,840.0 293.8 25 60.00 1.358 0.006

1.4

07/15/09 5,994,954.6 257.1 1,840.0 293.2 25 60.00 2.424 0.011

0.7

07/15/09 6,182,375.5 272.1 1,840.0 288.9 25 60.00 1.869 0.009

1.2

07/15/09 9,527,008.1 281.7 1,840.0 538.5 48 60.00 0.773 0.007

2.0

07/15/09 9,814,879.7 284.3 1,840.0 565.4 50 60.00 1.300 0.012

07/15/09 9,869,596.8 285.8 1,840.0 574.0 50 60.00 2.146 0.020
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00 2.1

1.7

07/18/09 5,776,168.5 243.4 1,840.0 298.2 25 60.00 2.538 0.012

1.5

07/18/09 5,702,397.5 242.6 1,840.0 297.5 25 60.00 2.033 0.010

1.5

07/18/09 5,707,515.0 241.5 1,840.0 294.7 25 60.00 1.813 0.009

2.0

07/18/09 5,747,936.1 240.8 1,840.0 296.8 25 60.00 1.813 0.009

1.6

07/18/09 5,703,714.9 242.0 1,840.0 294.5 25 60.00 2.417 0.011

1.7

07/18/09 5,648,026.8 243.9 1,840.0 294.7 25 60.00 1.914 0.009

1.5

07/18/09 5,698,644.3 243.5 1,840.0 294.2 25 60.00 2.055 0.010

2.1

07/18/09 5,708,036.3 242.4 1,840.0 294.7 25 60.00 1.813 0.009

2.3

07/18/09 5,674,557.5 241.3 1,840.0 296.1 25 60.00 2.512 0.012

1.6

07/18/09 5,649,554.6 242.2 1,840.0 291.7 25 60.00 2.780 0.013

1.5

07/18/09 5,689,270.9 243.7 1,840.0 293.7 25 60.00 1.934 0.009

1.4

07/18/09 5,687,763.0 242.9 1,840.0 293.7 25 60.00 1.813 0.009

1.3

07/18/09 5,728,088.4 240.6 1,840.0 292.6 25 60.00 1.710 0.008

2.0

07/18/09 5,699,556.7 237.0 1,840.0 294.3 25 60.00 1.571 0.007

1.9

07/18/09 5,614,424.6 234.9 1,840.0 292.9 25 60.00 2.392 0.011

1.9

07/18/09 5,613,276.1 233.9 1,840.0 292.9 25 60.00 2.272 0.011

1.7

07/18/09 5,597,782.1 233.8 1,840.0 292.1 25 60.00 2.272 0.011

1.7

07/18/09 5,587,767.0 235.2 1,840.0 288.5 25 60.00 2.055 0.009

1.5

07/18/09 5,593,476.8 236.0 1,840.0 282.7 25 60.00 2.099 0.009

1.2

07/18/09 5,576,935.3 236.1 1,840.0 287.9 25 60.00 1.813 0.008

1.4

07/18/09 5,641,314.0 236.5 1,840.0 291.2 25 60.00 1.450 0.007

1.5

07/17/09 5,625,397.7 238.0 1,840.0 290.4 25 60.00 1.692 0.008

1.7

07/17/09 5,531,248.7 238.1 1,840.0 288.6 25 60.00 1.794 0.008

1.7

07/17/09 5,638,691.0 237.8 1,840.0 291.1 25 60.00 2.055 0.010

2.6

07/17/09 5,645,392.9 237.4 1,840.0 291.5 25 60.00 2.055 0.010

2.2

07/17/09 5,592,588.9 239.1 1,840.0 291.8 25 60.00 3.110 0.015

1.9

07/17/09 5,598,710.4 244.4 1,840.0 289.1 25 60.00 2.659 0.012

2.4

07/17/09 5,634,773.3 251.4 1,840.0 290.9 25 60.00 2.296 0.011

2.8

07/17/09 5,765,035.7 263.5 1,840.0 288.3 25 60.00 2.995 0.014

3.1

07/17/09 9,383,609.9 272.4 1,840.0 525.3 47 60.00 3.121 0.026

2.8

07/17/09 9,734,715.6 272.4 1,840.0 555.5 50 60.00 3.390 0.030

2.6

07/17/09 9,752,845.3 274.0 1,840.0 551.3 50 60.00 3.091 0.027

2.2

07/17/09 9,759,501.7 273.6 1,840.0 551.7 50 60.00 2.870 0.025

2.1

07/17/09 9,728,274.9 271.3 1,840.0 555.1 50 60.00 2.406 0.021

1.4

07/17/09 9,755,860.0 263.8 1,840.0 556.7 50 60.00 2.296 0.020

1.2

07/17/09 8,997,064.7 243.3 1,840.0 508.5 45 60.00 1.546 0.013

07/17/09 5,552,549.5 234.8 1,840.0 286.7 25 60.00 1.450 0.007
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00 1.2

1.2

07/20/09 9,179,746.3 266.5 1,840.0 533.8 50 60.00 1.288 0.011

1.5

07/20/09 9,258,360.7 268.0 1,840.0 528.3 50 60.00 1.312 0.011

1.7

07/20/09 9,359,648.7 267.9 1,840.0 539.2 50 60.00 1.625 0.014

1.7

07/20/09 9,479,180.9 266.4 1,840.0 546.1 50 60.00 1.841 0.016

1.7

07/20/09 9,505,470.9 267.8 1,840.0 542.4 50 60.00 1.859 0.016

1.8

07/20/09 9,550,128.6 268.6 1,840.0 545.0 50 60.00 1.859 0.016

1.8

07/20/09 9,477,113.1 267.8 1,840.0 540.8 50 60.00 1.968 0.017

1.9

07/20/09 9,630,211.4 265.7 1,840.0 544.3 50 60.00 1.987 0.017

1.8

07/20/09 9,498,331.3 263.4 1,840.0 547.2 50 60.00 2.058 0.018

1.8

07/20/09 9,493,815.2 262.4 1,840.0 546.9 50 60.00 1.950 0.017

1.4

07/19/09 9,631,975.9 252.9 1,840.0 554.9 50 60.00 1.950 0.017

1.6

07/19/09 7,318,886.0 233.4 1,840.0 385.8 34 60.00 1.657 0.010

1.4

07/19/09 5,720,522.3 232.6 1,840.0 264.3 22 60.00 2.161 0.009

1.5

07/19/09 5,723,358.1 234.9 1,840.0 264.4 22 60.00 1.891 0.008

1.3

07/19/09 5,666,635.2 236.4 1,840.0 264.9 22 60.00 2.003 0.008

1.1

07/19/09 5,657,889.5 238.7 1,840.0 264.4 22 60.00 1.736 0.007

1.3

07/19/09 5,619,675.6 244.6 1,840.0 265.7 22 60.00 1.452 0.006

1.8

07/19/09 5,519,757.7 256.8 1,840.0 267.0 22 60.00 1.677 0.007

1.7

07/19/09 6,651,686.3 273.4 1,840.0 321.8 29 60.00 2.322 0.012

1.9

07/19/09 9,788,383.5 280.2 1,840.0 558.6 50 60.00 1.859 0.017

2.5

07/19/09 9,841,451.1 278.0 1,840.0 561.6 50 60.00 2.078 0.019

2.4

07/19/09 9,838,516.0 275.0 1,840.0 561.5 50 60.00 2.734 0.025

1.8

07/19/09 9,901,802.0 268.5 1,840.0 565.1 50 60.00 2.624 0.024

2.0

07/19/09 9,483,533.3 248.0 1,840.0 541.2 46 60.00 1.968 0.017

2.1

07/19/09 5,423,215.2 238.3 1,840.0 268.2 23 60.00 2.523 0.011

1.9

07/19/09 5,506,482.5 238.4 1,840.0 266.3 22 60.00 2.709 0.012

1.7

07/19/09 5,534,943.0 237.5 1,840.0 267.7 22 60.00 2.451 0.010

2.3

07/19/09 5,502,139.3 237.3 1,840.0 266.1 22 60.00 2.193 0.009

2.4

07/19/09 5,494,393.2 239.1 1,840.0 265.7 22 60.00 2.967 0.013

2.0

07/19/09 5,520,312.8 239.4 1,840.0 267.0 22 60.00 3.096 0.013

2.0

07/19/09 5,515,960.4 238.4 1,840.0 266.8 22 60.00 2.580 0.011

3.1

07/19/09 5,501,213.8 237.2 1,840.0 263.1 22 60.00 2.609 0.011

2.6

07/19/09 5,446,130.9 237.5 1,840.0 266.4 22 60.00 3.955 0.017

2.2

07/19/09 5,479,099.8 239.7 1,840.0 268.0 22 60.00 3.317 0.014

1.9

07/18/09 5,526,834.7 240.9 1,840.0 267.3 22 60.00 2.838 0.012

1.7

07/18/09 5,580,796.6 241.9 1,840.0 273.0 23 60.00 2.424 0.011

07/18/09 5,741,846.1 242.2 1,840.0 296.5 25 60.00 2.055 0.010
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00 1.4

1.6

07/21/09 5,772,634.5 262.8 1,840.0 301.2 25 60.00 1.674 0.008

1.6

07/21/09 6,607,915.7 280.8 1,840.0 344.8 30 60.00 1.914 0.011

1.7

07/21/09 10,563,312.9 292.4 1,840.0 620.0 55 60.00 1.701 0.017

1.7

07/21/09 10,558,698.8 293.7 1,840.0 625.5 55 60.00 1.791 0.018

1.8

07/21/09 10,532,406.3 293.9 1,840.0 623.9 55 60.00 1.791 0.018

1.7

07/21/09 10,601,341.2 292.4 1,840.0 628.0 55 60.00 1.896 0.019

1.6

07/21/09 10,574,518.9 290.2 1,840.0 626.5 55 60.00 1.791 0.018

1.5

07/21/09 10,555,486.9 288.3 1,840.0 625.3 55 60.00 1.685 0.017

1.5

07/21/09 10,551,707.1 287.1 1,840.0 625.1 55 60.00 1.580 0.016

1.5

07/21/09 10,602,369.7 289.4 1,840.0 622.3 55 60.00 1.595 0.016

1.5

07/21/09 10,612,578.2 290.9 1,840.0 622.9 55 60.00 1.595 0.016

1.6

07/21/09 10,638,455.6 290.4 1,840.0 630.2 55 60.00 1.580 0.016

1.5

07/21/09 10,637,844.4 286.7 1,840.0 630.2 55 60.00 1.685 0.017

1.5

07/21/09 10,478,516.1 279.3 1,840.0 620.8 54 60.00 1.580 0.016

1.2

07/21/09 9,908,759.9 274.3 1,840.0 576.2 50 60.00 1.610 0.015

0.7

07/21/09 9,984,355.7 263.0 1,840.0 580.6 50 60.00 1.288 0.012

0.7

07/21/09 7,493,688.8 238.9 1,840.0 419.5 35 60.00 0.780 0.005

1.0

07/21/09 5,782,778.5 235.1 1,840.0 301.7 25 60.00 0.837 0.004

1.2

07/21/09 5,582,409.1 236.1 1,840.0 276.1 23 60.00 1.262 0.006

1.2

07/21/09 5,590,162.6 236.5 1,840.0 273.4 22 60.00 1.531 0.007

1.2

07/21/09 5,565,187.3 235.6 1,840.0 269.2 22 60.00 1.548 0.007

2.0

07/21/09 5,571,295.3 234.8 1,840.0 272.5 22 60.00 1.531 0.007

1.9

07/21/09 5,507,220.3 234.3 1,840.0 272.4 22 60.00 2.523 0.011

1.5

07/20/09 5,536,029.0 235.4 1,840.0 273.8 22 60.00 2.397 0.010

1.3

07/20/09 5,564,044.3 239.4 1,840.0 272.2 22 60.00 1.914 0.008

1.4

07/20/09 5,590,840.8 245.4 1,840.0 270.4 22 60.00 1.677 0.007

1.5

07/20/09 5,684,094.6 255.8 1,840.0 271.8 22 60.00 1.827 0.008

1.5

07/20/09 7,288,234.0 269.7 1,840.0 372.3 33 60.00 1.832 0.011

1.4

07/20/09 9,689,782.9 275.6 1,840.0 568.8 50 60.00 1.595 0.015

1.5

07/20/09 9,695,659.9 276.3 1,840.0 569.1 50 60.00 1.488 0.014

1.5

07/20/09 9,732,693.6 275.0 1,840.0 571.3 50 60.00 1.595 0.015

1.2

07/20/09 9,835,157.3 271.7 1,840.0 566.6 50 60.00 1.625 0.015

1.5

07/20/09 9,316,155.2 270.5 1,840.0 541.7 50 60.00 1.288 0.011

1.6

07/20/09 9,701,801.5 273.1 1,840.0 564.2 50 60.00 1.610 0.015

1.5

07/20/09 9,660,306.0 271.6 1,840.0 567.0 50 60.00 1.701 0.015

1.5

07/20/09 9,826,236.5 268.3 1,840.0 555.4 50 60.00 1.656 0.015

07/20/09 9,480,867.2 265.5 1,840.0 541.0 50 60.00 1.640 0.014
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

23:00

00:00

01:00 C

02:00 C S S SC

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 0.9

0.9

07/23/09 5,894,085.0 241.4 1,840.0 307.5 25 60.00 1.076 0.005

0.8

07/23/09 5,896,315.2 240.7 1,840.0 307.6 25 60.00 1.076 0.005

0.9

07/23/09 5,888,439.1 240.1 1,840.0 307.2 25 60.00 0.957 0.005

0.7

07/23/09 5,877,187.5 240.4 1,840.0 306.6 25 60.00 1.076 0.005

0.6

07/23/09 5,857,507.6 240.8 1,840.0 302.5 25 60.00 0.846 0.004

0.6

07/23/09 5,867,074.0 240.2 1,840.0 302.9 25 60.00 0.725 0.004

0.7

07/23/09 5,775,008.5 241.8 1,840.0 301.3 25 60.00 0.718 0.003

0.7

07/23/09 5,925,766.3 244.7 1,840.0 302.7 25 60.00 0.855 0.004

0.7

07/23/09 5,912,256.2 246.1 1,840.0 302.0 25 60.00 0.855 0.004

0.8

07/23/09 5,927,886.1 246.9 1,840.0 302.8 25 60.00 0.855 0.004

1.1

07/23/09 5,929,854.5 247.4 1,840.0 302.9 25 60.00 0.977 0.005

1.2

07/23/09 5,947,438.5 248.7 1,840.0 303.8 25 60.00 1.344 0.007

1.3

07/22/09 5,947,011.0 253.5 1,840.0 303.8 25 60.00 1.466 0.007

1.6

07/22/09 5,958,872.8 266.0 1,840.0 301.2 25 60.00 1.605 0.008

1.8

07/22/09 7,049,699.0 284.9 1,840.0 364.0 32 60.00 1.934 0.011

1.8

07/22/09 10,766,485.9 292.7 1,840.0 631.9 55 60.00 1.914 0.019

2.1

07/22/09 10,744,235.4 292.7 1,840.0 630.6 55 60.00 1.914 0.019

2.1

07/22/09 10,721,688.8 291.2 1,840.0 629.3 55 60.00 2.233 0.022

1.8

07/22/09 10,718,549.8 289.6 1,840.0 629.2 55 60.00 2.233 0.022

1.7

07/22/09 10,723,750.5 289.4 1,840.0 629.5 55 60.00 1.914 0.019

1.8

07/22/09 10,746,073.0 289.3 1,840.0 630.7 55 60.00 1.807 0.018

1.8

07/22/09 10,736,757.1 287.3 1,840.0 630.2 55 60.00 1.914 0.019

2.0

07/22/09 10,745,123.0 284.2 1,840.0 630.7 55 60.00 1.914 0.019

1.7

07/22/09 10,719,041.8 282.9 1,840.0 629.2 55 60.00 2.126 0.021

1.4

07/22/09 10,733,945.8 279.6 1,840.0 630.0 55 60.00 1.807 0.018

0.9

07/22/09 10,399,403.9 266.2 1,840.0 604.7 52 60.00 1.502 0.015

1.0

07/22/09 8,097,714.4 245.7 1,840.0 448.9 38 60.00 1.013 0.007

0.8

07/22/09 5,810,520.8 242.2 1,840.0 303.2 25 60.00 1.196 0.006

0.8

07/22/09 5,829,997.6 241.7 1,840.0 301.0 25 60.00 0.967 0.005

1.1

07/22/09 5,841,065.5 240.8 1,840.0 304.7 25 60.00 0.957 0.005

1.4

07/22/09 5,761,050.5 240.1 1,840.0 300.6 25 60.00 1.316 0.006

1.2

07/22/09 5,769,924.2 241.4 1,840.0 301.0 25 60.00 1.674 0.008

1.2

07/22/09 5,796,171.2 244.3 1,840.0 299.3 25 60.00 1.450 0.007

0.9

07/22/09 5,840,933.6 245.5 1,840.0 304.7 25 60.00 1.435 0.007

0.9

07/22/09 5,828,856.1 246.2 1,840.0 304.1 25 60.00 1.076 0.005

1.2

07/22/09 5,804,241.5 247.4 1,840.0 302.8 25 60.00 1.076 0.005

07/21/09 5,769,696.5 252.0 1,840.0 301.0 25 60.00 1.435 0.007
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00 0.5

0.5

07/25/09 5,834,660.5 251.0 1,840.0 298.1 24 60.00 0.611 0.003

1.2

07/24/09 5,786,270.3 255.2 1,840.0 295.6 24 60.00 0.611 0.003

1.4

07/24/09 5,787,941.2 266.1 1,840.0 292.5 24 60.00 1.481 0.007

1.6

07/24/09 6,497,373.1 285.1 1,840.0 321.3 28 60.00 1.766 0.009

1.7

07/24/09 10,804,831.3 295.8 1,840.0 616.6 54 60.00 1.750 0.017

1.8

07/24/09 10,859,843.5 295.3 1,840.0 625.6 55 60.00 1.841 0.018

1.9

07/24/09 10,795,827.3 293.4 1,840.0 621.9 55 60.00 1.950 0.019

1.8

07/24/09 10,834,695.8 290.8 1,840.0 624.2 55 60.00 2.058 0.021

1.7

07/24/09 10,825,177.9 291.5 1,840.0 623.6 55 60.00 1.950 0.019

1.6

07/24/09 10,836,037.5 291.5 1,840.0 624.2 55 60.00 1.841 0.018

1.3

07/24/09 10,871,916.6 289.0 1,840.0 626.3 55 60.00 1.733 0.017

0.8

07/24/09 10,874,247.2 278.9 1,840.0 626.4 55 60.00 1.408 0.014

0.8

07/24/09 8,489,127.0 253.8 1,840.0 470.6 40 60.00 0.901 0.007

0.8

07/24/09 5,906,727.9 249.2 1,840.0 301.8 25 60.00 0.977 0.005

1.0

07/24/09 5,931,821.2 248.4 1,840.0 303.0 25 60.00 0.977 0.005

1.1

07/24/09 5,958,220.3 247.1 1,840.0 304.4 25 60.00 1.221 0.006

0.9

07/24/09 5,934,030.9 247.6 1,840.0 303.1 25 60.00 1.344 0.007

0.8

07/24/09 5,968,156.0 247.3 1,840.0 308.1 25 60.00 1.088 0.005

0.7

07/24/09 5,987,485.1 245.6 1,840.0 309.1 25 60.00 0.967 0.005

0.8

07/24/09 5,980,831.8 244.3 1,840.0 308.8 25 60.00 0.846 0.004

0.7

07/24/09 5,929,570.1 244.9 1,840.0 306.2 25 60.00 0.967 0.005

0.7

07/24/09 5,924,771.3 246.4 1,840.0 305.9 25 60.00 0.846 0.004

0.6

07/24/09 6,015,469.7 245.8 1,840.0 310.6 25 60.00 0.846 0.004

0.8

07/24/09 6,005,103.6 244.1 1,840.0 310.0 25 60.00 0.725 0.004

0.9

07/24/09 5,857,961.6 244.3 1,840.0 305.6 25 60.00 0.957 0.005

1.1

07/23/09 5,857,699.1 249.6 1,840.0 302.5 25 60.00 1.088 0.005

1.3

07/23/09 5,942,494.2 259.1 1,840.0 306.8 25 60.00 1.329 0.007

1.5

07/23/09 6,458,203.3 273.7 1,840.0 329.9 28 60.00 1.588 0.008

1.4

07/23/09 10,033,034.6 279.9 1,840.0 572.5 50 60.00 1.640 0.015

1.2

07/23/09 10,077,653.2 275.8 1,840.0 575.1 50 60.00 1.531 0.014

0.8

07/23/09 10,128,381.2 264.8 1,840.0 583.5 50 60.00 1.300 0.012

0.7

07/23/09 7,848,995.0 243.5 1,840.0 430.8 36 60.00 0.909 0.006

0.7

07/23/09 5,873,319.8 241.6 1,840.0 306.4 25 60.00 0.837 0.004

0.7

07/23/09 5,866,798.3 241.2 1,840.0 306.1 25 60.00 0.837 0.004

1.0

07/23/09 5,891,260.6 240.6 1,840.0 307.4 25 60.00 0.837 0.004

1.0

07/23/09 5,871,747.5 240.6 1,840.0 306.4 25 60.00 1.196 0.006

07/23/09 5,910,525.6 240.8 1,840.0 308.4 25 60.00 1.196 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00 1.3

1.3

07/26/09 10,659,730.1 294.4 1,840.0 637.3 55 60.00 1.357 0.014

1.0

07/26/09 10,659,693.7 290.2 1,840.0 637.3 55 60.00 1.357 0.014

0.6

07/26/09 10,626,691.8 285.5 1,840.0 635.3 55 60.00 1.044 0.011

0.3

07/26/09 10,628,917.0 272.7 1,840.0 629.7 55 60.00 0.632 0.006

0.3

07/26/09 7,450,941.2 245.7 1,840.0 400.9 33 60.00 0.348 0.002

0.4

07/26/09 5,616,911.6 244.1 1,840.0 280.9 22 60.00 0.374 0.002

0.3

07/26/09 5,663,975.5 245.3 1,840.0 289.4 23 60.00 0.489 0.002

0.3

07/26/09 5,783,251.5 244.2 1,840.0 301.7 24 60.00 0.359 0.002

0.6

07/26/09 5,729,990.0 242.4 1,840.0 299.0 24 60.00 0.359 0.002

0.5

07/26/09 5,722,469.6 241.2 1,840.0 298.5 24 60.00 0.718 0.003

0.5

07/26/09 5,759,527.4 242.0 1,840.0 294.3 24 60.00 0.611 0.003

0.4

07/26/09 5,806,818.5 245.0 1,840.0 293.5 24 60.00 0.617 0.003

0.5

07/26/09 5,866,147.8 245.6 1,840.0 296.5 24 60.00 0.494 0.002

0.5

07/26/09 5,791,146.8 244.7 1,840.0 295.8 24 60.00 0.611 0.003

0.8

07/25/09 5,743,573.6 243.8 1,840.0 296.6 24 60.00 0.604 0.003

0.8

07/25/09 5,705,555.0 244.1 1,840.0 294.6 24 60.00 0.967 0.005

0.5

07/25/09 5,684,947.0 247.6 1,840.0 293.5 24 60.00 0.967 0.005

0.6

07/25/09 5,750,163.5 256.1 1,840.0 296.9 24 60.00 0.604 0.003

0.9

07/25/09 5,760,823.1 269.3 1,840.0 294.3 24 60.00 0.733 0.003

1.0

07/25/09 8,183,628.8 283.0 1,840.0 427.0 38 60.00 1.076 0.007

1.0

07/25/09 10,063,259.7 288.0 1,840.0 568.8 50 60.00 1.104 0.010

0.6

07/25/09 10,779,263.9 286.8 1,840.0 626.8 54 60.00 1.073 0.011

0.6

07/25/09 10,784,674.9 267.5 1,840.0 627.2 54 60.00 0.644 0.006

0.6

07/25/09 6,290,184.7 247.9 1,840.0 335.0 27 60.00 0.703 0.004

0.5

07/25/09 5,744,158.3 247.4 1,840.0 299.7 24 60.00 0.718 0.003

0.5

07/25/09 5,753,293.3 245.8 1,840.0 300.2 24 60.00 0.598 0.003

0.5

07/25/09 5,725,666.4 244.9 1,840.0 295.6 24 60.00 0.604 0.003

0.4

07/25/09 5,702,554.3 245.0 1,840.0 297.5 24 60.00 0.598 0.003

0.4

07/25/09 5,709,557.3 243.9 1,840.0 294.8 24 60.00 0.483 0.002

0.5

07/25/09 5,729,476.1 243.1 1,840.0 295.8 24 60.00 0.483 0.002

0.6

07/25/09 5,683,964.1 243.1 1,840.0 293.5 24 60.00 0.604 0.003

0.5

07/25/09 5,691,534.0 243.9 1,840.0 293.9 24 60.00 0.725 0.003

0.4

07/25/09 5,707,215.9 245.1 1,840.0 294.7 24 60.00 0.604 0.003

0.5

07/25/09 5,800,267.9 245.1 1,840.0 293.2 24 60.00 0.494 0.002

0.6

07/25/09 5,783,760.6 244.7 1,840.0 292.3 24 60.00 0.617 0.003

0.5

07/25/09 5,769,463.2 246.9 1,840.0 291.6 24 60.00 0.741 0.003

07/25/09 5,763,597.8 248.9 1,840.0 294.5 24 60.00 0.611 0.003
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00 S S S

20:00 S S S

21:00

22:00

23:00

00:00

01:00

02:00 C S S 0.9 S

0.8

07/28/09 5,861,836.9 246.6 1,840.0 289.9 23 60.00 1.136 0.005

0.6

07/28/09 5,876,662.1 248.4 1,840.0 287.5 23 60.00 1.021 0.005

0.6

07/28/09 5,846,648.4 252.9 1,840.0 289.2 23 60.00 0.757 0.004

1.1

07/27/09 5,653,267.4 263.2 1,840.0 285.7 23 60.00 0.741 0.003

0.9

07/27/09 7,713,088.7 277.9 1,840.0 389.8 35 60.00 1.358 0.008

0.9

07/27/09 9,876,658.1 283.1 1,840.0 552.9 50 60.00 1.003 0.009

0.9

07/27/09 9,875,965.9 283.6 1,840.0 552.8 50 60.00 1.003 0.009

0.8

07/27/09 9,885,580.4 284.2 1,840.0 553.4 50 60.00 1.003 0.009

1.0

07/27/09 9,773,571.9 284.8 1,840.0 563.1 50 60.00 0.867 0.008

0.9

07/27/09 9,938,003.9 289.9 1,840.0 572.5 50 60.00 1.083 0.010

1.1

07/27/09 10,470,214.3 296.5 1,840.0 620.2 54 60.00 0.948 0.009

1.1

07/27/09 10,705,376.1 296.8 1,840.0 640.0 55 60.00 1.148 0.012

1.0

07/27/09 10,565,161.3 291.5 1,840.0 625.9 54 60.00 1.159 0.012

1.0

07/27/09 10,035,901.2 291.1 1,840.0 578.2 50 60.00 1.083 0.010

1.1

07/27/09 10,037,820.8 292.6 1,840.0 583.7 50 60.00 1.073 0.010

1.1

07/27/09 10,069,428.8 291.7 1,840.0 585.5 50 60.00 1.180 0.011

1.1

07/27/09 10,050,051.4 288.8 1,840.0 579.0 50 60.00 1.191 0.011

1.1

07/27/09 10,032,160.5 284.0 1,840.0 583.4 51 60.00 1.180 0.011

0.7

07/27/09 10,068,450.8 274.0 1,840.0 580.0 50 60.00 1.191 0.011

0.7

07/27/09 9,126,216.3 248.9 1,840.0 520.8 44 60.00 0.765 0.006

0.5

07/27/09 5,702,377.5 238.9 1,840.0 297.5 24 60.00 0.837 0.004

0.6

07/27/09 5,707,943.4 241.4 1,840.0 294.7 24 60.00 0.604 0.003

0.6

07/27/09 5,718,353.4 243.8 1,840.0 295.2 24 60.00 0.725 0.003

0.5

07/27/09 5,796,057.0 244.8 1,840.0 296.1 24 60.00 0.733 0.003

0.7

07/27/09 5,769,758.2 244.9 1,840.0 288.5 24 60.00 0.624 0.003

0.5

07/27/09 5,774,031.0 246.8 1,840.0 295.0 24 60.00 0.855 0.004

0.7

07/27/09 5,827,109.8 249.8 1,840.0 297.7 24 60.00 0.611 0.003

0.8

07/26/09 5,745,046.8 255.7 1,840.0 296.6 24 60.00 0.846 0.004

1.1

07/26/09 5,748,433.0 268.5 1,840.0 293.6 24 60.00 0.977 0.005

1.1

07/26/09 8,304,565.9 282.9 1,840.0 446.8 40 60.00 1.276 0.009

1.1

07/26/09 9,938,460.6 287.8 1,840.0 572.5 50 60.00 1.191 0.011

1.3

07/26/09 9,945,989.1 289.3 1,840.0 573.0 50 60.00 1.191 0.011

1.3

07/26/09 9,905,120.1 289.5 1,840.0 576.0 50 60.00 1.395 0.013

1.6

07/26/09 9,864,927.7 289.6 1,840.0 573.7 50 60.00 1.395 0.013

1.3

07/26/09 10,444,154.8 291.1 1,840.0 624.4 54 60.00 1.670 0.017

1.2

07/26/09 10,492,337.6 293.1 1,840.0 627.2 55 60.00 1.357 0.014

07/26/09 10,623,395.1 295.3 1,840.0 635.1 55 60.00 1.253 0.013
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00 1.8

1.7

07/29/09 10,017,722.1 287.2 1,840.0 566.2 50 60.00 1.987 0.018

1.5

07/29/09 9,721,181.3 287.7 1,840.0 554.7 48 60.00 1.859 0.016

1.3

07/29/09 9,521,547.3 287.6 1,840.0 548.5 47 60.00 1.625 0.014

1.1

07/29/09 9,514,149.9 287.5 1,840.0 542.9 47 60.00 1.422 0.012

1.1

07/29/09 9,525,723.2 285.8 1,840.0 543.6 47 60.00 1.203 0.010

1.1

07/29/09 9,497,394.6 282.9 1,840.0 541.9 47 60.00 1.203 0.010

0.9

07/29/09 9,503,325.1 278.3 1,840.0 542.3 47 60.00 1.203 0.010

0.5

07/29/09 9,638,451.9 269.9 1,840.0 550.0 48 60.00 0.984 0.009

0.5

07/29/09 8,146,908.1 247.6 1,840.0 456.1 38 60.00 0.557 0.004

0.4

07/29/09 5,803,847.8 243.7 1,840.0 299.7 25 60.00 0.604 0.003

0.4

07/29/09 5,802,889.8 243.6 1,840.0 299.6 25 60.00 0.483 0.002

0.3

07/29/09 5,676,204.6 243.8 1,840.0 293.1 24 60.00 0.483 0.002

0.4

07/29/09 5,635,383.0 244.0 1,840.0 290.9 24 60.00 0.363 0.002

0.4

07/29/09 5,591,457.8 244.7 1,840.0 288.7 24 60.00 0.483 0.002

0.7

07/29/09 5,596,937.6 246.0 1,840.0 289.0 24 60.00 0.483 0.002

0.6

07/29/09 5,572,475.6 249.9 1,840.0 290.7 24 60.00 0.837 0.004

0.7

07/28/09 5,632,190.3 259.6 1,840.0 290.8 24 60.00 0.725 0.003

1.1

07/28/09 5,644,500.9 275.4 1,840.0 288.4 24 60.00 0.855 0.004

1.1

07/28/09 9,011,012.4 289.2 1,840.0 509.3 45 60.00 1.214 0.010

1.2

07/28/09 9,994,102.2 290.0 1,840.0 581.2 51 60.00 1.180 0.011

1.2

07/28/09 9,992,466.7 289.7 1,840.0 581.1 51 60.00 1.288 0.012

1.3

07/28/09 9,991,878.4 292.0 1,840.0 581.1 51 60.00 1.288 0.012

1.4

07/28/09 9,962,172.7 292.6 1,840.0 579.3 51 60.00 1.395 0.013

1.4

07/28/09 9,959,366.7 292.3 1,840.0 584.6 50 60.00 1.488 0.014

1.4

07/28/09 9,997,075.3 291.3 1,840.0 581.3 50 60.00 1.502 0.014

1.6

07/28/09 9,997,067.3 289.7 1,840.0 586.8 50 60.00 1.488 0.014

1.4

07/28/09 10,002,521.0 288.8 1,840.0 581.7 50 60.00 1.717 0.016

1.2

07/28/09 10,028,155.7 290.6 1,840.0 583.1 50 60.00 1.502 0.014

1.3

07/28/09 10,012,426.1 290.1 1,840.0 587.7 50 60.00 1.276 0.012

1.4

07/28/09 10,018,467.5 287.8 1,840.0 582.6 50 60.00 1.395 0.013

1.3

07/28/09 9,983,021.5 283.0 1,840.0 586.0 50 60.00 1.488 0.014

0.8

07/28/09 9,985,909.2 275.6 1,840.0 586.1 50 60.00 1.382 0.013

0.7

07/28/09 9,793,816.4 257.5 1,840.0 569.5 48 60.00 0.858 0.008

0.5

07/28/09 5,911,627.8 244.0 1,840.0 295.6 24 60.00 0.874 0.004

1.0

07/28/09 5,803,841.9 243.2 1,840.0 290.2 23 60.00 0.624 0.003

0.9

07/28/09 5,690,398.5 242.6 1,840.0 284.5 23 60.00 1.248 0.006

07/28/09 5,733,862.2 243.8 1,840.0 283.6 23 60.00 1.136 0.005
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 0.3 C

0.2

07/31/09 5,739,811.1 241.2 1,840.0 296.4 24 60.00 0.363 0.002

0.2

07/31/09 5,684,461.3 241.2 1,840.0 293.5 24 60.00 0.242 0.001

0.3

07/31/09 5,718,210.8 242.0 1,840.0 292.1 24 60.00 0.244 0.001

0.3

07/31/09 5,701,831.8 243.7 1,840.0 294.4 24 60.00 0.363 0.002

0.3

07/31/09 5,707,311.6 244.8 1,840.0 294.7 24 60.00 0.363 0.002

0.5

07/30/09 5,684,723.7 246.4 1,840.0 293.5 24 60.00 0.363 0.002

0.5

07/30/09 5,724,177.7 249.8 1,840.0 295.5 24 60.00 0.604 0.003

0.8

07/30/09 5,743,845.4 257.9 1,840.0 296.6 24 60.00 0.604 0.003

1.0

07/30/09 5,674,034.3 271.8 1,840.0 289.9 24 60.00 0.977 0.005

1.1

07/30/09 8,874,779.4 283.4 1,840.0 492.0 43 60.00 1.126 0.009

1.2

07/30/09 9,944,296.2 284.3 1,840.0 572.9 50 60.00 1.191 0.011

1.2

07/30/09 9,936,558.6 283.4 1,840.0 572.5 50 60.00 1.300 0.012

1.1

07/30/09 10,015,950.2 283.5 1,840.0 577.0 50 60.00 1.300 0.012

1.0

07/30/09 9,972,714.2 283.2 1,840.0 569.1 50 60.00 1.203 0.011

1.1

07/30/09 10,029,853.2 282.5 1,840.0 572.4 50 60.00 1.093 0.010

1.0

07/30/09 10,020,220.9 280.7 1,840.0 571.8 50 60.00 1.203 0.011

0.9

07/30/09 10,041,836.0 279.1 1,840.0 567.6 50 60.00 1.104 0.010

0.9

07/30/09 9,802,383.4 281.0 1,840.0 559.4 50 60.00 0.984 0.009

0.9

07/30/09 9,793,383.5 281.7 1,840.0 558.8 50 60.00 0.984 0.009

0.9

07/30/09 9,830,976.8 281.4 1,840.0 561.0 50 60.00 0.984 0.009

0.7

07/30/09 9,805,044.1 279.3 1,840.0 559.5 50 60.00 0.984 0.009

0.7

07/30/09 9,870,288.8 275.9 1,840.0 563.2 50 60.00 0.765 0.007

0.6

07/30/09 9,918,282.9 262.5 1,840.0 576.8 50 60.00 0.751 0.007

0.4

07/30/09 7,042,469.3 244.2 1,840.0 378.9 31 60.00 0.696 0.004

0.4

07/30/09 5,711,602.1 244.8 1,840.0 291.8 24 60.00 0.489 0.002

0.4

07/30/09 5,651,503.8 245.4 1,840.0 291.8 24 60.00 0.483 0.002

0.4

07/30/09 5,625,887.6 245.6 1,840.0 290.5 24 60.00 0.483 0.002

0.4

07/30/09 5,601,435.0 246.6 1,840.0 289.2 24 60.00 0.483 0.002

0.5

07/30/09 5,633,796.3 249.1 1,840.0 290.9 24 60.00 0.483 0.002

0.8

07/29/09 5,645,475.6 254.9 1,840.0 294.5 24 60.00 0.598 0.003

1.2

07/29/09 5,737,199.9 268.2 1,840.0 296.2 24 60.00 0.967 0.005

1.4

07/29/09 7,572,054.5 283.1 1,840.0 399.2 35 60.00 1.420 0.009

1.4

07/29/09 9,925,677.9 288.0 1,840.0 571.8 50 60.00 1.516 0.014

1.5

07/29/09 9,937,851.5 289.4 1,840.0 567.1 50 60.00 1.531 0.014

1.8

07/29/09 9,928,321.8 289.7 1,840.0 566.5 50 60.00 1.640 0.015

2.1

07/29/09 9,862,500.1 287.9 1,840.0 568.2 50 60.00 1.950 0.018

07/29/09 9,998,492.6 286.1 1,840.0 570.5 50 60.00 2.296 0.021
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00 0.5

0.2

08/01/09 9,865,525.4 263.5 1,840.0 568.4 50 60.00 0.542 0.005

0.2

08/01/09 6,880,303.8 242.9 1,840.0 373.9 32 60.00 0.230 0.001

0.3

08/01/09 5,562,955.5 240.7 1,840.0 287.2 24 60.00 0.242 0.001

0.2

08/01/09 5,515,141.3 240.8 1,840.0 284.7 24 60.00 0.363 0.002

0.2

08/01/09 5,546,040.6 240.8 1,840.0 286.3 24 60.00 0.242 0.001

0.2

08/01/09 5,544,590.8 239.2 1,840.0 286.3 24 60.00 0.242 0.001

0.1

08/01/09 5,575,271.8 237.0 1,840.0 287.8 24 60.00 0.242 0.001

0.2

08/01/09 5,560,843.2 236.0 1,840.0 284.1 24 60.00 0.122 0.001

0.2

08/01/09 5,558,875.8 236.6 1,840.0 287.0 24 60.00 0.242 0.001

0.2

08/01/09 5,530,243.5 236.1 1,840.0 285.5 24 60.00 0.242 0.001

0.2

08/01/09 5,576,283.9 235.3 1,840.0 284.9 24 60.00 0.244 0.001

0.2

08/01/09 5,578,070.7 235.6 1,840.0 285.0 24 60.00 0.244 0.001

0.1

08/01/09 5,583,569.1 237.4 1,840.0 285.3 24 60.00 0.244 0.001

0.2

08/01/09 5,554,918.2 238.9 1,840.0 283.8 24 60.00 0.122 0.001

0.2

08/01/09 5,567,642.4 241.7 1,840.0 284.5 24 60.00 0.244 0.001

0.3

08/01/09 5,646,078.2 247.9 1,840.0 282.3 24 60.00 0.250 0.001

0.6

08/01/09 5,610,947.6 258.9 1,840.0 286.6 24 60.00 0.366 0.002

0.8

08/01/09 6,675,140.6 275.1 1,840.0 341.0 30 60.00 0.733 0.004

0.8

07/31/09 9,691,488.9 284.4 1,840.0 553.0 48 60.00 0.875 0.008

0.9

07/31/09 10,013,388.9 284.1 1,840.0 576.8 50 60.00 0.867 0.008

0.8

07/31/09 10,003,630.3 282.1 1,840.0 576.3 50 60.00 0.975 0.009

0.7

07/31/09 10,035,729.0 281.1 1,840.0 572.7 50 60.00 0.875 0.008

0.7

07/31/09 10,060,926.9 283.1 1,840.0 568.7 50 60.00 0.773 0.007

0.7

07/31/09 10,043,784.6 284.3 1,840.0 573.2 50 60.00 0.765 0.007

0.7

07/31/09 10,075,294.8 284.5 1,840.0 580.4 50 60.00 0.758 0.007

0.7

07/31/09 10,034,106.5 283.7 1,840.0 578.0 50 60.00 0.758 0.007

0.7

07/31/09 10,039,666.9 284.4 1,840.0 572.9 50 60.00 0.765 0.007

0.7

07/31/09 10,101,857.5 285.3 1,840.0 582.0 50 60.00 0.758 0.007

0.8

07/31/09 10,186,149.0 284.5 1,840.0 586.8 51 60.00 0.758 0.007

0.8

07/31/09 9,966,149.2 283.0 1,840.0 574.1 49 60.00 0.867 0.008

0.7

07/31/09 10,214,974.9 281.8 1,840.0 594.0 51 60.00 0.858 0.008

0.4

07/31/09 10,144,632.4 276.1 1,840.0 578.9 50 60.00 0.765 0.007

0.4

07/31/09 9,657,811.3 256.6 1,840.0 540.6 47 60.00 0.446 0.004

0.4

07/31/09 6,049,675.3 244.0 1,840.0 318.9 26 60.00 0.473 0.002

0.5

07/31/09 5,888,245.5 242.8 1,840.0 307.2 25 60.00 0.478 0.002

0.3

07/31/09 5,894,311.5 242.4 1,840.0 307.5 25 60.00 0.598 0.003

07/31/09 5,878,153.7 241.8 1,840.0 306.7 25 60.00 0.359 0.002
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00 0.3

0.2

08/03/09 8,719,336.9 239.9 1,840.0 497.6 43 60.00 0.328 0.003

0.4

08/03/09 5,320,298.8 229.8 1,840.0 268.9 22 60.00 0.247 0.001

0.3

08/03/09 5,258,014.2 229.7 1,840.0 265.8 22 60.00 0.494 0.002

0.3

08/03/09 5,236,521.1 231.5 1,840.0 264.7 22 60.00 0.370 0.002

0.3

08/03/09 5,311,372.5 232.8 1,840.0 262.7 22 60.00 0.379 0.002

0.3

08/03/09 5,320,146.5 233.6 1,840.0 268.9 22 60.00 0.370 0.002

0.5

08/03/09 5,305,780.3 234.7 1,840.0 268.2 22 60.00 0.370 0.002

0.5

08/02/09 5,311,752.6 237.1 1,840.0 268.5 22 60.00 0.617 0.003

0.5

08/02/09 5,284,952.1 244.2 1,840.0 270.0 22 60.00 0.611 0.003

0.7

08/02/09 5,395,445.5 256.8 1,840.0 269.8 22 60.00 0.624 0.003

0.8

08/02/09 7,313,777.7 271.4 1,840.0 369.7 33 60.00 0.864 0.005

0.8

08/02/09 9,755,803.7 274.5 1,840.0 556.7 50 60.00 0.875 0.008

0.6

08/02/09 9,688,428.6 271.6 1,840.0 558.1 49 60.00 0.867 0.008

0.3

08/02/09 9,800,921.4 267.6 1,840.0 564.6 50 60.00 0.650 0.006

0.0

08/02/09 9,635,047.1 252.1 1,840.0 555.1 48 60.00 0.325 0.003

0.0

08/02/09 6,212,256.8 235.5 1,840.0 324.1 27 60.00 0.000 0.000

0.0

08/02/09 5,573,730.9 232.0 1,840.0 266.6 22 60.00 0.000 0.000

0.1

08/02/09 5,016,608.5 232.4 1,840.0 223.6 19 60.00 0.000 0.000

0.1

08/02/09 5,345,117.6 233.0 1,840.0 217.9 19 60.00 0.153 0.001

0.0

08/02/09 6,075,455.2 233.4 1,840.0 224.5 19 60.00 0.169 0.001

0.1

08/02/09 5,873,314.1 233.1 1,840.0 223.4 18 60.00 0.000 0.000

0.1

08/02/09 5,288,432.8 232.7 1,840.0 241.4 19 60.00 0.137 0.001

0.1

08/02/09 5,117,318.8 232.3 1,840.0 239.2 19 60.00 0.134 0.001

0.1

08/02/09 5,064,883.1 231.8 1,840.0 239.5 19 60.00 0.132 0.001

0.2

08/02/09 5,095,719.4 233.0 1,840.0 238.2 19 60.00 0.134 0.001

0.4

08/02/09 5,260,149.0 236.7 1,840.0 245.8 20 60.00 0.267 0.001

0.3

08/02/09 5,607,121.0 239.3 1,840.0 286.4 24 60.00 0.489 0.002

0.3

08/02/09 5,590,190.3 239.6 1,840.0 285.6 24 60.00 0.366 0.002

0.3

08/02/09 5,584,688.6 239.5 1,840.0 282.3 24 60.00 0.370 0.002

0.5

08/02/09 5,620,973.0 239.4 1,840.0 287.2 24 60.00 0.366 0.002

0.4

08/02/09 5,618,661.0 241.1 1,840.0 287.1 24 60.00 0.611 0.003

0.5

08/01/09 5,619,875.9 246.1 1,840.0 284.1 24 60.00 0.494 0.002

0.5

08/01/09 5,621,045.2 253.1 1,840.0 287.2 24 60.00 0.611 0.003

0.7

08/01/09 5,612,796.5 265.0 1,840.0 283.7 24 60.00 0.617 0.003

0.7

08/01/09 8,041,088.2 277.5 1,840.0 428.3 39 60.00 0.820 0.006

0.7

08/01/09 9,764,622.7 277.6 1,840.0 557.2 50 60.00 0.765 0.007

08/01/09 9,728,364.9 275.0 1,840.0 560.4 50 60.00 0.758 0.007
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00 1.3

1.3

08/04/09 9,828,587.4 282.3 1,840.0 566.2 50 60.00 1.408 0.013

1.2

08/04/09 9,822,709.7 284.3 1,840.0 565.9 50 60.00 1.408 0.013

1.2

08/04/09 9,859,016.1 284.5 1,840.0 568.0 50 60.00 1.300 0.012

1.2

08/04/09 9,870,803.8 283.3 1,840.0 568.7 50 60.00 1.300 0.012

1.2

08/04/09 9,823,003.1 281.4 1,840.0 565.9 50 60.00 1.300 0.012

1.1

08/04/09 9,803,325.2 280.3 1,840.0 564.7 50 60.00 1.300 0.012

1.0

08/04/09 9,833,181.0 282.2 1,840.0 561.1 50 60.00 1.203 0.011

1.0

08/04/09 9,800,962.3 282.4 1,840.0 564.6 50 60.00 1.083 0.010

1.0

08/04/09 9,811,952.6 281.4 1,840.0 565.3 50 60.00 1.083 0.010

1.0

08/04/09 9,805,946.7 280.4 1,840.0 564.9 50 60.00 1.083 0.010

1.0

08/04/09 9,828,182.2 280.6 1,840.0 566.2 50 60.00 1.083 0.010

0.9

08/04/09 9,831,513.9 278.7 1,840.0 566.4 50 60.00 1.083 0.010

0.7

08/04/09 9,872,172.5 268.8 1,840.0 568.7 50 60.00 0.975 0.009

0.9

08/04/09 8,425,366.8 243.0 1,840.0 471.6 40 60.00 0.780 0.006

0.9

08/04/09 5,417,553.7 238.3 1,840.0 270.9 22 60.00 1.123 0.005

0.8

08/04/09 5,772,639.4 240.5 1,840.0 273.0 22 60.00 1.188 0.005

0.7

08/04/09 5,718,729.8 240.7 1,840.0 270.4 22 60.00 1.056 0.005

0.6

08/04/09 5,625,415.5 241.4 1,840.0 262.9 22 60.00 0.935 0.004

0.8

08/04/09 5,621,953.9 242.9 1,840.0 271.9 22 60.00 0.774 0.003

0.7

08/04/09 5,562,183.3 246.3 1,840.0 281.1 22 60.00 0.988 0.004

0.7

08/03/09 5,462,852.9 254.6 1,840.0 276.1 22 60.00 0.864 0.004

1.0

08/03/09 5,509,115.5 268.7 1,840.0 275.4 22 60.00 0.874 0.004

1.2

08/03/09 7,559,832.8 284.4 1,840.0 386.2 34 60.00 1.221 0.008

1.3

08/03/09 10,006,500.0 288.4 1,840.0 565.6 48 60.00 1.325 0.012

1.4

08/03/09 9,998,285.3 287.1 1,840.0 570.5 49 60.00 1.422 0.013

1.2

08/03/09 10,005,800.0 287.3 1,840.0 565.6 50 60.00 1.546 0.014

1.1

08/03/09 9,994,067.9 287.9 1,840.0 564.9 50 60.00 1.325 0.012

1.3

08/03/09 9,916,953.2 288.2 1,840.0 565.9 50 60.00 1.203 0.011

1.1

08/03/09 9,892,694.1 286.9 1,840.0 564.5 50 60.00 1.422 0.013

1.0

08/03/09 9,906,152.7 284.2 1,840.0 565.3 50 60.00 1.203 0.011

0.9

08/03/09 9,902,558.9 281.6 1,840.0 565.1 50 60.00 1.093 0.010

0.9

08/03/09 9,845,981.5 282.0 1,840.0 556.5 50 60.00 0.994 0.009

0.9

08/03/09 9,836,720.4 280.7 1,840.0 561.4 50 60.00 0.984 0.009

0.8

08/03/09 9,833,422.2 277.7 1,840.0 561.1 50 60.00 0.984 0.009

0.8

08/03/09 9,778,582.1 273.5 1,840.0 558.0 50 60.00 0.875 0.008

0.7

08/03/09 9,759,733.9 270.4 1,840.0 557.0 50 60.00 0.875 0.008

08/03/09 9,799,629.9 263.4 1,840.0 559.2 50 60.00 0.765 0.007
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C S S SC

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00 0.5

0.0

08/06/09 9,891,574.6 255.4 1,840.0 564.5 50 60.00 0.547 0.005

0.1

08/06/09 6,533,257.9 231.7 1,840.0 355.1 29 60.00 0.000 0.000

0.1

08/06/09 4,908,982.3 228.5 1,840.0 245.4 19 60.00 0.125 0.000

0.1

08/06/09 4,928,316.3 230.3 1,840.0 243.7 19 60.00 0.126 0.000

0.1

08/06/09 5,032,478.7 232.6 1,840.0 246.1 19 60.00 0.128 0.001

0.0

08/06/09 4,986,911.8 234.1 1,840.0 243.9 19 60.00 0.128 0.000

0.1

08/06/09 5,101,768.7 237.3 1,840.0 249.6 19 60.00 0.000 0.000

0.3

08/06/09 4,958,601.5 242.1 1,840.0 242.6 19 60.00 0.128 0.000

0.4

08/06/09 5,571,139.1 247.9 1,840.0 287.6 24 60.00 0.363 0.002

0.7

08/05/09 5,772,538.5 253.5 1,840.0 310.6 26 60.00 0.464 0.002

1.1

08/05/09 5,784,845.8 264.5 1,840.0 308.1 26 60.00 0.820 0.004

1.2

08/05/09 7,793,038.8 277.0 1,840.0 432.0 39 60.00 1.238 0.009

1.1

08/05/09 9,549,559.3 280.5 1,840.0 570.9 50 60.00 1.253 0.011

1.0

08/05/09 9,566,256.4 280.8 1,840.0 571.9 50 60.00 1.148 0.010

1.1

08/05/09 9,487,987.6 280.1 1,840.0 567.2 50 60.00 1.044 0.009

1.0

08/05/09 9,542,689.2 278.9 1,840.0 570.5 50 60.00 1.148 0.010

1.0

08/05/09 9,577,273.5 280.2 1,840.0 572.5 50 60.00 1.044 0.010

1.2

08/05/09 9,538,301.4 280.8 1,840.0 570.2 50 60.00 1.044 0.010

1.3

08/05/09 9,591,527.6 280.2 1,840.0 573.4 50 60.00 1.253 0.011

1.1

08/05/09 9,590,410.3 279.2 1,840.0 573.3 50 60.00 1.357 0.012

1.1

08/05/09 9,572,464.8 280.1 1,840.0 572.2 50 60.00 1.148 0.011

1.5

08/05/09 9,585,226.5 280.3 1,840.0 578.2 50 60.00 1.138 0.011

1.3

08/05/09 9,781,117.5 279.5 1,840.0 574.1 50 60.00 1.595 0.015

1.2

08/05/09 9,856,539.9 277.2 1,840.0 573.2 50 60.00 1.395 0.013

0.7

08/05/09 9,930,076.6 273.4 1,840.0 577.5 50 60.00 1.288 0.012

0.3

08/05/09 10,027,224.4 257.3 1,840.0 583.1 50 60.00 0.751 0.007

0.2

08/05/09 6,382,978.5 237.6 1,840.0 350.4 28 60.00 0.341 0.002

0.3

08/05/09 5,564,973.7 238.7 1,840.0 293.4 24 60.00 0.237 0.001

0.4

08/05/09 5,637,315.6 241.1 1,840.0 294.1 24 60.00 0.359 0.002

0.4

08/05/09 5,603,854.2 241.8 1,840.0 292.4 24 60.00 0.478 0.002

0.5

08/05/09 5,563,774.3 242.0 1,840.0 290.3 24 60.00 0.478 0.002

0.4

08/05/09 5,556,842.5 242.0 1,840.0 286.9 24 60.00 0.604 0.003

0.4

08/05/09 5,583,041.1 243.7 1,840.0 291.3 24 60.00 0.478 0.002

0.5

08/04/09 5,549,753.8 249.6 1,840.0 286.5 24 60.00 0.483 0.002

0.9

08/04/09 5,559,773.1 260.4 1,840.0 287.1 24 60.00 0.604 0.003

1.3

08/04/09 5,974,218.3 275.9 1,840.0 301.9 26 60.00 1.111 0.005

08/04/09 9,668,229.7 283.3 1,840.0 557.0 49 60.00 1.408 0.013
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00 1.3

1.3

08/07/09 9,977,679.7 285.5 1,840.0 574.8 51 60.00 1.408 0.013

1.4

08/07/09 9,967,325.5 284.5 1,840.0 574.2 51 60.00 1.408 0.013

1.3

08/07/09 9,930,342.3 282.9 1,840.0 577.5 51 60.00 1.502 0.014

1.2

08/07/09 9,945,746.9 282.7 1,840.0 578.4 51 60.00 1.395 0.013

1.2

08/07/09 9,996,442.7 285.3 1,840.0 575.9 51 60.00 1.300 0.012

1.2

08/07/09 9,962,508.5 286.8 1,840.0 574.0 51 60.00 1.300 0.012

1.3

08/07/09 9,989,769.7 286.4 1,840.0 580.9 51 60.00 1.288 0.012

1.3

08/07/09 10,044,475.9 284.6 1,840.0 578.6 51 60.00 1.408 0.013

1.2

08/07/09 10,010,102.5 282.1 1,840.0 576.7 51 60.00 1.408 0.013

1.0

08/07/09 9,986,642.7 281.3 1,840.0 580.8 51 60.00 1.288 0.012

1.0

08/07/09 10,009,845.4 282.1 1,840.0 582.1 51 60.00 1.073 0.010

0.9

08/07/09 9,975,658.1 280.8 1,840.0 580.1 51 60.00 1.073 0.010

0.8

08/07/09 9,983,146.5 275.7 1,840.0 580.5 51 60.00 0.966 0.009

0.4

08/07/09 10,031,057.7 263.9 1,840.0 583.3 51 60.00 0.858 0.008

0.3

08/07/09 7,966,112.9 241.1 1,840.0 450.3 38 60.00 0.442 0.003

0.2

08/07/09 5,480,935.2 236.7 1,840.0 288.9 24 60.00 0.355 0.002

0.2

08/07/09 5,511,274.2 235.1 1,840.0 290.5 24 60.00 0.237 0.001

0.2

08/07/09 5,490,397.3 236.5 1,840.0 289.4 24 60.00 0.237 0.001

0.2

08/07/09 5,474,387.1 238.8 1,840.0 285.6 24 60.00 0.239 0.001

0.3

08/07/09 5,534,928.6 240.6 1,840.0 291.8 24 60.00 0.237 0.001

0.3

08/07/09 5,535,558.3 240.8 1,840.0 288.8 24 60.00 0.359 0.002

0.4

08/07/09 5,525,010.8 241.3 1,840.0 288.3 24 60.00 0.359 0.002

0.7

08/06/09 5,511,740.9 243.1 1,840.0 287.6 24 60.00 0.478 0.002

0.8

08/06/09 5,517,098.0 250.2 1,840.0 287.8 24 60.00 0.837 0.004

1.1

08/06/09 5,451,855.6 265.7 1,840.0 281.5 24 60.00 0.967 0.004

1.2

08/06/09 8,661,713.2 282.7 1,840.0 475.5 43 60.00 1.250 0.010

1.2

08/06/09 9,997,573.1 284.1 1,840.0 581.4 52 60.00 1.288 0.012

1.3

08/06/09 9,960,703.0 284.3 1,840.0 579.3 51 60.00 1.288 0.012

1.4

08/06/09 10,019,308.4 283.0 1,840.0 588.1 52 60.00 1.382 0.013

1.3

08/06/09 9,993,709.5 281.2 1,840.0 586.6 51 60.00 1.488 0.014

1.1

08/06/09 9,951,939.3 282.0 1,840.0 584.1 52 60.00 1.382 0.013

1.1

08/06/09 9,969,408.1 284.0 1,840.0 585.1 52 60.00 1.169 0.011

1.1

08/06/09 9,984,450.7 284.4 1,840.0 586.0 51 60.00 1.169 0.011

1.3

08/06/09 10,006,847.1 283.0 1,840.0 587.4 52 60.00 1.169 0.011

1.2

08/06/09 9,971,917.7 278.9 1,840.0 590.7 51 60.00 1.369 0.013

1.0

08/06/09 10,005,608.6 275.3 1,840.0 587.3 51 60.00 1.276 0.012

08/06/09 9,676,602.1 270.0 1,840.0 557.5 50 60.00 1.083 0.010
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00 0.9

0.6

08/09/09 9,971,798.2 285.0 1,840.0 569.1 50 60.00 0.984 0.009

0.1

08/09/09 10,005,702.6 282.1 1,840.0 565.6 50 60.00 0.662 0.006

0.0

08/09/09 9,272,201.0 276.0 1,840.0 564.4 50 60.00 0.103 0.001

0.2

08/09/09 8,707,965.7 264.5 1,840.0 553.7 50 60.00 0.000 0.000

0.5

08/09/09 7,015,952.2 244.6 1,840.0 404.2 36 60.00 0.217 0.001

0.4

08/09/09 5,560,816.3 243.3 1,840.0 290.1 24 60.00 0.598 0.003

0.3

08/09/09 5,580,917.2 245.6 1,840.0 291.2 24 60.00 0.478 0.002

0.3

08/09/09 5,602,451.7 247.0 1,840.0 289.2 24 60.00 0.363 0.002

0.3

08/09/09 5,689,152.2 247.3 1,840.0 296.8 24 60.00 0.359 0.002

0.4

08/09/09 5,670,072.6 248.3 1,840.0 292.7 24 60.00 0.363 0.002

0.8

08/09/09 5,601,061.9 252.8 1,840.0 289.2 24 60.00 0.483 0.002

0.9

08/08/09 5,592,141.9 263.4 1,840.0 288.7 24 60.00 0.967 0.004

1.1

08/08/09 6,341,049.2 280.5 1,840.0 323.9 28 60.00 1.099 0.006

1.1

08/08/09 9,885,573.0 289.1 1,840.0 569.5 50 60.00 1.191 0.011

1.0

08/08/09 9,907,048.6 289.8 1,840.0 570.7 50 60.00 1.191 0.011

1.1

08/08/09 9,924,322.7 288.9 1,840.0 566.3 50 60.00 1.093 0.010

1.1

08/08/09 9,920,671.9 285.5 1,840.0 566.1 50 60.00 1.203 0.011

1.2

08/08/09 9,921,497.1 282.6 1,840.0 566.1 50 60.00 1.203 0.011

1.0

08/08/09 9,946,046.9 279.4 1,840.0 567.6 50 60.00 1.312 0.012

1.0

08/08/09 9,852,975.9 278.4 1,840.0 556.9 50 60.00 1.104 0.010

1.2

08/08/09 9,862,183.1 278.5 1,840.0 557.4 50 60.00 1.104 0.010

0.7

08/08/09 10,091,478.8 275.7 1,840.0 559.4 50 60.00 1.351 0.012

0.6

08/08/09 10,335,966.6 263.4 1,840.0 561.7 50 60.00 0.804 0.007

0.6

08/08/09 7,119,232.8 239.1 1,840.0 379.2 31 60.00 0.703 0.004

0.4

08/08/09 5,644,879.7 237.3 1,840.0 291.5 24 60.00 0.725 0.003

0.4

08/08/09 5,589,516.0 236.3 1,840.0 288.6 24 60.00 0.483 0.002

0.4

08/08/09 5,662,642.5 235.9 1,840.0 292.4 24 60.00 0.483 0.002

0.5

08/08/09 5,673,433.3 235.9 1,840.0 292.9 24 60.00 0.483 0.002

0.5

08/08/09 5,642,154.3 235.7 1,840.0 291.3 24 60.00 0.604 0.003

0.3

08/08/09 5,603,131.9 236.9 1,840.0 289.3 24 60.00 0.604 0.003

0.3

08/08/09 5,549,808.1 237.1 1,840.0 286.5 24 60.00 0.363 0.002

0.3

08/08/09 5,631,382.3 238.2 1,840.0 287.7 24 60.00 0.366 0.002

0.5

08/08/09 5,542,800.5 238.9 1,840.0 283.2 24 60.00 0.366 0.002

0.5

08/08/09 5,531,379.8 242.4 1,840.0 282.6 24 60.00 0.611 0.003

0.7

08/08/09 5,590,369.7 250.5 1,840.0 285.6 24 60.00 0.611 0.003

1.1

08/07/09 5,592,703.5 263.4 1,840.0 285.7 24 60.00 0.855 0.004

08/07/09 6,840,534.9 279.9 1,840.0 353.2 31 60.00 1.329 0.008
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00 S S S

20:00 S S S

21:00

22:00

23:00 0.9

1.0

08/10/09 9,482,446.4 282.0 1,840.0 561.7 50 60.00 0.948 0.009

1.0

08/10/09 9,605,806.1 284.7 1,840.0 558.6 50 60.00 1.073 0.010

1.1

08/10/09 9,644,565.8 285.4 1,840.0 560.9 50 60.00 1.073 0.010

1.1

08/10/09 9,637,747.1 285.5 1,840.0 560.5 50 60.00 1.180 0.011

1.1

08/10/09 9,572,848.9 284.7 1,840.0 561.9 50 60.00 1.169 0.011

1.0

08/10/09 9,681,047.6 282.3 1,840.0 563.0 50 60.00 1.180 0.011

1.0

08/10/09 9,648,216.9 282.6 1,840.0 561.1 50 60.00 1.073 0.010

1.1

08/10/09 9,671,487.3 284.8 1,840.0 562.4 50 60.00 1.073 0.010

1.0

08/10/09 9,718,231.9 285.4 1,840.0 559.8 50 60.00 1.191 0.011

1.1

08/10/09 9,788,883.5 285.3 1,840.0 569.3 51 60.00 1.073 0.010

1.0

08/10/09 9,721,677.6 281.7 1,840.0 575.9 51 60.00 1.159 0.011

0.9

08/10/09 9,374,292.5 281.4 1,840.0 545.1 48 60.00 1.073 0.009

0.9

08/10/09 9,557,675.2 284.5 1,840.0 555.8 49 60.00 0.966 0.009

0.8

08/10/09 9,849,449.8 285.8 1,840.0 572.7 51 60.00 0.966 0.009

0.7

08/10/09 10,000,109.0 283.2 1,840.0 581.5 51 60.00 0.858 0.008

0.6

08/10/09 9,922,498.2 282.3 1,840.0 577.0 51 60.00 0.751 0.007

0.4

08/10/09 9,836,490.7 280.2 1,840.0 577.3 51 60.00 0.638 0.006

0.3

08/10/09 9,242,749.1 275.3 1,840.0 567.6 51 60.00 0.406 0.004

0.2

08/10/09 8,991,973.8 268.8 1,840.0 566.9 50 60.00 0.297 0.003

0.3

08/10/09 8,670,480.5 254.4 1,840.0 541.9 48 60.00 0.200 0.002

0.2

08/10/09 5,655,041.3 248.5 1,840.0 295.0 25 60.00 0.359 0.002

0.3

08/10/09 5,572,707.0 251.4 1,840.0 290.8 24 60.00 0.239 0.001

0.4

08/10/09 5,593,409.9 257.9 1,840.0 285.7 24 60.00 0.366 0.002

0.5

08/10/09 5,694,996.2 272.3 1,840.0 284.8 25 60.00 0.499 0.002

0.4

08/09/09 8,555,992.4 280.6 1,840.0 530.1 47 60.00 0.504 0.004

0.5

08/09/09 8,943,019.9 281.2 1,840.0 563.8 50 60.00 0.396 0.004

0.6

08/09/09 8,926,616.0 281.7 1,840.0 557.9 50 60.00 0.499 0.004

0.6

08/09/09 8,982,578.4 283.8 1,840.0 561.4 50 60.00 0.599 0.005

0.9

08/09/09 8,976,481.3 286.9 1,840.0 561.0 50 60.00 0.599 0.005

0.8

08/09/09 9,588,834.5 290.5 1,840.0 562.8 50 60.00 0.957 0.009

0.9

08/09/09 9,633,133.5 289.4 1,840.0 565.4 50 60.00 0.850 0.008

0.9

08/09/09 9,483,608.5 287.7 1,840.0 567.0 50 60.00 0.939 0.009

0.8

08/09/09 9,525,882.2 287.5 1,840.0 564.3 50 60.00 0.948 0.009

0.7

08/09/09 9,557,611.4 288.8 1,840.0 566.2 50 60.00 0.843 0.008

0.7

08/09/09 9,566,096.3 289.2 1,840.0 566.7 50 60.00 0.737 0.007

0.8

08/09/09 9,519,285.5 288.7 1,840.0 563.9 50 60.00 0.737 0.007

08/09/09 9,590,652.4 287.4 1,840.0 563.0 50 60.00 0.850 0.008
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00 S S S

09:00 M

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 C

02:00 C C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00 1.5

1.1

08/12/09 9,697,841.8 275.2 1,840.0 564.0 49 60.00 1.610 0.015

1.0

08/12/09 9,557,964.5 271.7 1,840.0 555.8 50 60.00 1.180 0.010

1.0

08/12/09 9,116,360.4 266.1 1,840.0 540.0 49 60.00 1.053 0.009

0.4

08/12/09 8,818,652.2 262.5 1,840.0 546.4 51 60.00 1.007 0.009

0.4

08/12/09 9,610,392.2 253.6 1,840.0 564.1 51 60.00 0.425 0.004

0.4

08/12/09 6,033,580.1 239.4 1,840.0 327.9 28 60.00 0.459 0.002

0.3

08/12/09 5,674,881.1 239.6 1,840.0 296.1 25 60.00 0.478 0.002

0.4

08/12/09 5,645,316.9 240.6 1,840.0 297.6 25 60.00 0.355 0.002

0.4

08/12/09 5,513,762.0 242.9 1,840.0 290.7 24 60.00 0.473 0.002

0.4

08/12/09 5,515,590.5 245.6 1,840.0 287.8 24 60.00 0.478 0.002

0.4

08/12/09 5,557,692.8 250.0 1,840.0 290.0 24 60.00 0.478 0.002

1.0

08/12/09 5,568,184.2 258.4 1,840.0 287.5 24 60.00 0.483 0.002

1.4

08/12/09 5,972,462.1 272.7 1,840.0 305.1 27 60.00 1.221 0.006

1.3

08/11/09 9,575,850.8 279.4 1,840.0 562.1 50 60.00 1.488 0.013

1.2

08/11/09 9,617,371.9 278.0 1,840.0 569.7 50 60.00 1.369 0.012

0.8

08/11/09 9,683,777.9 277.3 1,840.0 568.4 50 60.00 1.276 0.012

0.8

08/11/09 9,331,655.4 275.3 1,840.0 542.7 48 60.00 0.858 0.007

1.1

08/11/09 8,985,999.5 277.5 1,840.0 532.3 48 60.00 0.843 0.007

1.2

08/11/09 9,416,562.1 279.6 1,840.0 547.6 50 60.00 1.180 0.010

1.2

08/11/09 9,419,223.4 281.1 1,840.0 558.0 50 60.00 1.264 0.011

1.2

08/11/09 9,545,775.9 283.2 1,840.0 565.5 50 60.00 1.264 0.011

1.4

08/11/09 9,669,787.6 283.6 1,840.0 567.6 50 60.00 1.276 0.012

1.1

08/11/09 9,730,378.1 282.7 1,840.0 565.8 50 60.00 1.502 0.014

1.0

08/11/09 9,666,409.9 281.2 1,840.0 562.1 50 60.00 1.180 0.011

1.0

08/11/09 9,594,174.2 280.7 1,840.0 563.1 50 60.00 1.063 0.010

1.0

08/11/09 9,666,201.1 280.5 1,840.0 562.1 50 60.00 1.073 0.010

1.0

08/11/09 9,527,247.3 282.3 1,840.0 564.4 50 60.00 1.053 0.010

1.0

08/11/09 9,476,720.9 284.0 1,840.0 566.6 50 60.00 1.044 0.009

1.0

08/11/09 9,531,827.0 283.9 1,840.0 564.7 50 60.00 1.053 0.010

0.9

08/11/09 9,631,524.4 282.0 1,840.0 565.4 50 60.00 1.063 0.010

0.9

08/11/09 9,167,971.2 279.2 1,840.0 528.2 46 60.00 0.975 0.008

1.0

08/11/09 8,928,809.7 279.8 1,840.0 509.5 45 60.00 0.984 0.008

0.9

08/11/09 9,525,903.6 281.1 1,840.0 554.0 49 60.00 1.073 0.010

0.9

08/11/09 9,570,401.8 281.7 1,840.0 561.7 50 60.00 0.957 0.009

0.8

08/11/09 9,517,831.2 283.1 1,840.0 553.5 50 60.00 0.966 0.009

0.8

08/11/09 9,547,289.3 283.5 1,840.0 560.4 50 60.00 0.850 0.008

08/11/09 9,498,289.1 282.8 1,840.0 562.7 50 60.00 0.843 0.008
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 0.9

0.9

08/14/09 5,740,369.1 244.2 1,840.0 287.0 24 60.00 1.123 0.005

1.2

08/14/09 5,784,909.1 247.1 1,840.0 289.3 24 60.00 1.123 0.005

1.8

08/13/09 5,770,871.7 254.1 1,840.0 285.4 24 60.00 1.514 0.007

1.6

08/13/09 7,712,764.6 265.2 1,840.0 389.8 36 60.00 2.222 0.014

1.6

08/13/09 9,419,286.0 267.6 1,840.0 522.1 48 60.00 1.801 0.015

1.6

08/13/09 9,494,873.3 268.7 1,840.0 526.4 48 60.00 1.801 0.015

1.6

08/13/09 9,664,982.5 270.7 1,840.0 546.3 50 60.00 1.766 0.015

1.5

08/13/09 9,760,315.4 271.1 1,840.0 546.3 50 60.00 1.784 0.016

1.4

08/13/09 9,576,806.3 273.5 1,840.0 546.5 50 60.00 1.640 0.014

1.4

08/13/09 9,583,553.5 275.6 1,840.0 541.7 50 60.00 1.546 0.013

1.5

08/13/09 9,691,010.8 275.3 1,840.0 547.8 50 60.00 1.546 0.014

1.5

08/13/09 9,608,115.6 274.7 1,840.0 548.3 50 60.00 1.640 0.014

1.7

08/13/09 9,727,712.7 278.5 1,840.0 549.8 50 60.00 1.656 0.015

1.7

08/13/09 10,240,801.3 280.2 1,840.0 562.1 50 60.00 1.933 0.017

1.6

08/13/09 10,181,014.7 279.8 1,840.0 558.8 50 60.00 1.933 0.017

1.5

08/13/09 10,201,983.4 279.5 1,840.0 565.5 50 60.00 1.801 0.016

1.3

08/13/09 10,186,706.2 277.4 1,840.0 564.7 50 60.00 1.688 0.015

0.8

08/13/09 10,140,543.3 274.3 1,840.0 562.2 50 60.00 1.463 0.013

0.1

08/13/09 10,293,369.0 263.8 1,840.0 565.0 50 60.00 0.909 0.008

0.0

08/13/09 8,020,073.9 243.8 1,840.0 418.4 35 60.00 0.120 0.001

0.0

08/13/09 5,810,584.5 240.9 1,840.0 296.9 24 60.00 0.000 0.000

0.0

08/13/09 5,806,124.4 241.1 1,840.0 296.6 24 60.00 0.000 0.000

0.0

08/13/09 5,744,555.4 241.9 1,840.0 296.6 24 60.00 0.000 0.000

0.0

08/13/09 5,689,656.7 245.1 1,840.0 303.1 24 60.00 0.000 0.000

0.0

08/13/09 5,595,029.7 249.3 1,840.0 288.9 24 60.00 0.000 0.000

0.8

08/13/09 5,660,015.8 258.5 1,840.0 295.3 24 60.00 0.000 0.000

1.7

08/12/09 6,175,000.9 273.1 1,840.0 308.8 27 60.00 0.998 0.005

1.7

08/12/09 9,970,767.2 280.4 1,840.0 569.0 50 60.00 1.859 0.017

1.6

08/12/09 9,905,715.3 279.9 1,840.0 570.7 50 60.00 1.841 0.017

1.5

08/12/09 9,808,108.5 279.1 1,840.0 570.4 50 60.00 1.717 0.016

1.5

08/12/09 9,735,514.5 278.5 1,840.0 571.5 50 60.00 1.595 0.015

1.5

08/12/09 9,670,614.0 279.8 1,840.0 567.6 50 60.00 1.595 0.014

1.5

08/12/09 9,818,030.4 281.7 1,840.0 570.9 50 60.00 1.610 0.015

1.5

08/12/09 9,789,830.8 281.8 1,840.0 574.6 50 60.00 1.595 0.015

1.5

08/12/09 9,738,681.9 281.7 1,840.0 571.6 50 60.00 1.595 0.015

1.5

08/12/09 9,902,053.6 281.4 1,840.0 570.4 50 60.00 1.625 0.015

08/12/09 9,926,538.6 279.4 1,840.0 571.9 50 60.00 1.625 0.015
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00 S S S

16:00 S S S

17:00 S S S

18:00 S S S

19:00 S S S

20:00 S S S

21:00 S S S

22:00 S S S

23:00 S S S

00:00 S S S

01:00 S S S

02:00 C S S S

03:00 S S S

04:00 ST ST STC

05:00 C ST ST STC

06:00 ST ST ST

07:00 ST ST ST

08:00 ST ST ST

09:00 ST ST ST

10:00 ST ST ST

11:00 ST ST ST

12:00 ST ST ST

13:00 ST ST ST

14:00 ST ST 1.7 ST

1.7

08/15/09 10,088,057.3 280.7 1,840.0 564.7 50 60.00 1.895 0.017

1.7

08/15/09 9,803,050.4 280.1 1,840.0 554.1 50 60.00 1.877 0.017

1.7

08/15/09 9,804,477.6 280.4 1,840.0 554.1 50 60.00 1.877 0.017

1.7

08/15/09 9,806,031.5 279.0 1,840.0 554.3 50 60.00 1.877 0.017

1.7

08/15/09 9,723,980.8 275.4 1,840.0 549.6 50 60.00 1.877 0.016

1.7

08/15/09 9,622,670.4 271.6 1,840.0 549.1 50 60.00 1.859 0.016

1.7

08/15/09 9,848,889.9 258.8 1,840.0 572.7 51 60.00 1.824 0.017

1.7

08/15/09 6,361,462.6 242.1 1,840.0 338.8 28 60.00 1.992 0.011

1.7

08/15/09 5,633,208.7 241.4 1,840.0 287.8 24 60.00 2.076 0.010

1.7

08/15/09 5,658,986.5 242.8 1,840.0 286.0 24 60.00 2.099 0.010

1.7

08/15/09 5,669,440.9 244.4 1,840.0 286.5 24 60.00 2.099 0.010

1.7

08/15/09 5,688,066.5 246.4 1,840.0 287.5 24 60.00 2.099 0.010

1.7

08/15/09 5,728,350.3 250.2 1,840.0 283.3 24 60.00 2.145 0.010

1.7

08/15/09 5,719,703.9 257.7 1,840.0 286.0 24 60.00 2.122 0.010

1.7

08/15/09 5,612,185.7 272.3 1,840.0 277.6 24 60.00 2.145 0.010

1.7

08/14/09 9,141,201.8 283.4 1,840.0 506.7 45 60.00 1.914 0.016

1.7

08/14/09 9,781,428.5 283.1 1,840.0 552.8 49 60.00 1.877 0.017

1.7

08/14/09 9,773,901.9 282.3 1,840.0 552.4 49 60.00 1.877 0.017

1.7

08/14/09 9,728,423.6 281.0 1,840.0 549.8 49 60.00 1.877 0.017

1.7

08/14/09 9,720,081.6 280.9 1,840.0 554.7 49 60.00 1.859 0.016

1.7

08/14/09 9,765,147.4 281.8 1,840.0 551.9 49 60.00 1.877 0.017

1.7

08/14/09 9,750,605.9 281.6 1,840.0 551.1 49 60.00 1.877 0.017

1.7

08/14/09 9,752,902.8 280.7 1,840.0 551.3 49 60.00 1.877 0.017

1.6

08/14/09 9,747,505.3 279.8 1,840.0 551.0 49 60.00 1.877 0.017

1.6

08/14/09 9,742,351.6 280.1 1,840.0 550.6 49 60.00 1.766 0.016

1.2

08/14/09 9,753,730.5 280.6 1,840.0 556.6 49 60.00 1.750 0.016

1.7

08/14/09 9,833,938.2 279.9 1,840.0 555.8 49 60.00 1.325 0.012

1.7

08/14/09 9,842,329.1 278.5 1,840.0 556.3 49 60.00 1.877 0.017

1.8

08/14/09 9,749,309.0 277.3 1,840.0 556.3 49 60.00 1.859 0.017

1.7

08/14/09 9,616,175.6 275.3 1,840.0 548.7 49 60.00 1.968 0.017

1.6

08/14/09 9,776,385.4 274.0 1,840.0 531.3 50 60.00 1.952 0.017

1.2

08/14/09 10,196,594.9 272.3 1,840.0 543.1 50 60.00 1.875 0.016

0.7

08/14/09 10,469,831.1 262.7 1,840.0 557.6 50 60.00 1.406 0.013

0.7

08/14/09 7,457,104.7 241.0 1,840.0 393.1 33 60.00 0.829 0.005

0.9

08/14/09 5,679,750.1 238.5 1,840.0 287.1 24 60.00 0.864 0.004

1.0

08/14/09 5,719,690.0 239.3 1,840.0 289.1 24 60.00 1.111 0.005

08/14/09 5,763,277.8 242.1 1,840.0 285.0 24 60.00 1.262 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

15:00 ST ST ST

16:00 ST ST ST

17:00 ST ST ST

18:00 ST ST ST

19:00 ST ST ST

20:00 ST ST ST

21:00 ST ST ST

22:00 ST ST ST

23:00 ST ST ST

00:00 ST ST ST

01:00 ST ST ST

02:00 C ST ST ST

03:00 ST ST ST

04:00 ST ST STC

05:00 C ST ST STC

06:00 ST ST ST

07:00 ST ST ST

08:00 ST ST ST

09:00 ST ST ST

10:00 ST ST ST

11:00 ST ST ST

12:00 ST ST ST

13:00 ST ST ST

14:00 ST ST ST

15:00 ST ST ST

16:00 ST ST ST

17:00 ST ST ST

18:00 ST ST ST

19:00 ST ST ST

20:00 ST ST ST

21:00 ST ST ST

22:00 ST ST ST

23:00 ST ST ST

00:00 ST ST ST

01:00 ST ST ST

02:00 C ST ST ST

03:00 ST ST 1.7 ST

1.7

08/17/09 5,578,766.0 239.7 1,840.0 272.9 23 60.00 2.169 0.009

1.7

08/17/09 5,509,955.5 240.9 1,840.0 272.5 23 60.00 2.145 0.009

1.7

08/17/09 5,497,013.6 244.3 1,840.0 274.9 23 60.00 2.122 0.009

1.7

08/17/09 5,573,768.0 250.5 1,840.0 272.6 23 60.00 2.169 0.009

1.7

08/16/09 5,619,939.6 260.9 1,840.0 271.8 23 60.00 2.193 0.010

1.7

08/16/09 6,779,436.3 274.3 1,840.0 338.9 31 60.00 2.122 0.011

1.7

08/16/09 9,351,273.6 281.8 1,840.0 518.4 47 60.00 1.914 0.016

1.7

08/16/09 9,859,733.0 283.3 1,840.0 557.3 50 60.00 1.877 0.017

1.7

08/16/09 9,858,445.6 283.2 1,840.0 551.8 50 60.00 1.895 0.017

1.7

08/16/09 9,848,039.1 282.4 1,840.0 551.3 50 60.00 1.895 0.017

1.7

08/16/09 9,864,274.8 281.0 1,840.0 557.5 50 60.00 1.877 0.017

1.7

08/16/09 9,911,205.4 279.8 1,840.0 560.2 50 60.00 1.877 0.017

1.7

08/16/09 9,869,076.2 279.4 1,840.0 557.8 50 60.00 1.877 0.017

1.7

08/16/09 9,862,044.9 277.9 1,840.0 552.1 49 60.00 1.895 0.017

1.7

08/16/09 9,868,806.8 276.1 1,840.0 552.4 49 60.00 1.895 0.017

1.7

08/16/09 9,788,337.8 274.8 1,840.0 553.2 50 60.00 1.877 0.017

1.7

08/16/09 9,809,582.2 273.5 1,840.0 554.5 49 60.00 1.877 0.017

1.7

08/16/09 9,757,418.3 271.9 1,840.0 546.2 49 60.00 1.895 0.017

1.7

08/16/09 9,883,394.3 265.1 1,840.0 553.2 50 60.00 1.895 0.017

1.7

08/16/09 8,881,669.9 243.8 1,840.0 487.5 43 60.00 1.933 0.015

1.7

08/16/09 5,524,332.6 236.0 1,840.0 285.2 25 60.00 2.055 0.009

1.7

08/16/09 5,714,149.2 236.1 1,840.0 285.7 25 60.00 2.122 0.010

1.7

08/16/09 5,629,121.5 236.0 1,840.0 287.6 25 60.00 2.076 0.010

1.7

08/16/09 5,723,315.5 237.2 1,840.0 289.3 25 60.00 2.099 0.010

1.7

08/16/09 5,623,942.2 238.1 1,840.0 290.4 25 60.00 2.055 0.010

1.7

08/16/09 5,586,430.4 240.3 1,840.0 294.5 25 60.00 2.012 0.009

1.7

08/16/09 5,682,669.7 242.3 1,840.0 293.4 25 60.00 2.055 0.010

1.7

08/16/09 5,728,610.6 247.2 1,840.0 289.6 25 60.00 2.099 0.010

1.7

08/15/09 5,774,685.8 258.0 1,840.0 295.0 26 60.00 2.076 0.010

1.7

08/15/09 7,747,246.7 270.4 1,840.0 391.6 36 60.00 2.099 0.013

1.7

08/15/09 9,255,795.7 273.0 1,840.0 498.0 45 60.00 1.972 0.016

1.7

08/15/09 9,256,678.0 273.7 1,840.0 498.1 45 60.00 1.972 0.016

1.7

08/15/09 9,160,701.8 274.8 1,840.0 502.9 45 60.00 1.933 0.016

1.7

08/15/09 9,217,549.0 278.4 1,840.0 511.0 46 60.00 1.914 0.016

1.7

08/15/09 9,657,851.3 282.8 1,840.0 551.1 49 60.00 1.859 0.016

1.7

08/15/09 9,987,085.2 283.2 1,840.0 564.5 50 60.00 1.877 0.017

08/15/09 9,974,606.8 281.7 1,840.0 563.8 50 60.00 1.877 0.017
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

04:00 ST ST STC

05:00 C ST ST STC

06:00 ST ST ST

07:00 ST ST ST

08:00 ST ST ST

09:00 ST ST ST

10:00 ST ST ST

11:00 ST ST ST

12:00 ST ST ST

13:00 ST ST STC

14:00 ST ST STC

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00 M

09:00 S S S

10:00 S S S

11:00 S S S

12:00 S S SC

13:00 C

14:00

15:00

16:00 1.5

1.4

08/18/09 9,770,371.5 282.0 1,840.0 557.5 50 60.00 1.640 0.015

1.1

08/18/09 9,906,979.4 278.5 1,840.0 560.0 50 60.00 1.546 0.014

1.2

08/18/09 8,850,958.6 276.9 1,840.0 500.3 45 60.00 1.214 0.010

1.3

08/18/09 9,361,589.6 282.1 1,840.0 534.2 49 60.00 1.312 0.011

1.3

08/18/09 9,908,644.8 282.6 1,840.0 570.8 51 60.00 1.408 0.013

1.3

08/18/09 9,998,368.1 283.6 1,840.0 570.5 51 60.00 1.422 0.013

1.3

08/18/09 9,984,867.3 282.7 1,840.0 569.8 51 60.00 1.422 0.013

1.4

08/18/09 9,978,293.6 279.7 1,840.0 569.4 51 60.00 1.422 0.013

1.2

08/18/09 9,833,111.8 275.4 1,840.0 555.8 50 60.00 1.546 0.014

0.7

08/18/09 9,811,297.0 269.4 1,840.0 559.9 50 60.00 1.312 0.012

0.6

08/18/09 8,934,862.4 248.6 1,840.0 500.2 44 60.00 0.780 0.006

0.6

08/18/09 5,904,380.2 241.3 1,840.0 308.0 26 60.00 0.718 0.004

0.5

08/18/09 5,837,097.1 242.6 1,840.0 304.5 26 60.00 0.718 0.003

0.5

08/18/09 5,787,556.9 243.8 1,840.0 302.0 26 60.00 0.598 0.003

0.5

08/18/09 5,880,392.8 245.1 1,840.0 300.4 26 60.00 0.611 0.003

0.7

08/18/09 5,841,983.3 248.4 1,840.0 301.6 26 60.00 0.604 0.003

1.1

08/18/09 5,805,477.9 257.9 1,840.0 299.7 26 60.00 0.846 0.004

1.4

08/17/09 6,621,495.3 270.4 1,840.0 331.1 30 60.00 1.373 0.007

1.4

08/17/09 9,271,467.8 273.7 1,840.0 508.9 45 60.00 1.592 0.013

1.5

08/17/09 9,249,624.2 272.2 1,840.0 512.8 46 60.00 1.576 0.013

1.5

08/17/09 9,176,189.6 273.6 1,840.0 508.7 45 60.00 1.688 0.014

1.5

08/17/09 9,619,323.1 276.4 1,840.0 538.5 48 60.00 1.672 0.014

1.6

08/17/09 9,805,730.1 276.8 1,840.0 554.3 50 60.00 1.656 0.015

1.5

08/17/09 9,684,125.2 277.5 1,840.0 542.1 48 60.00 1.784 0.015

1.4

08/17/09 10,048,641.7 278.0 1,840.0 562.5 51 60.00 1.672 0.015

1.7

08/17/09 10,078,763.3 275.0 1,840.0 542.3 50 60.00 1.624 0.014

1.7

08/17/09 9,773,867.6 273.9 1,840.0 531.2 50 60.00 1.952 0.017

1.7

08/17/09 9,641,631.6 274.6 1,840.0 534.5 50 60.00 1.914 0.016

1.7

08/17/09 9,337,544.9 276.8 1,840.0 517.6 47 60.00 1.914 0.016

1.7

08/17/09 9,724,565.4 276.2 1,840.0 544.4 49 60.00 1.895 0.016

1.7

08/17/09 9,688,589.5 275.5 1,840.0 547.6 49 60.00 1.877 0.016

1.7

08/17/09 9,647,275.4 277.1 1,840.0 545.3 49 60.00 1.877 0.016

1.7

08/17/09 9,828,049.0 275.6 1,840.0 555.5 50 60.00 1.877 0.017

1.7

08/17/09 9,801,559.4 271.9 1,840.0 554.0 50 60.00 1.877 0.017

1.7

08/17/09 9,857,174.7 261.8 1,840.0 557.1 50 60.00 1.877 0.017

1.7

08/17/09 7,587,079.3 242.1 1,840.0 412.3 36 60.00 1.952 0.013

08/17/09 5,603,903.6 240.0 1,840.0 277.2 23 60.00 2.145 0.010
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 S S SC

02:00 C S S SC

03:00 S S S

04:00 S S SC

05:00 C C

06:00

07:00

08:00

09:00

10:00 * *

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 S S SC

05:00 C 0.2 C

0.2

08/20/09 5,542,914.8 233.9 1,840.0 298.2 25 60.00 0.232 0.001

0.2

08/20/09 5,489,175.0 232.7 1,840.0 295.3 25 60.00 0.232 0.001

0.2

08/20/09 5,434,949.4 233.3 1,840.0 289.5 24 60.00 0.234 0.001

0.3

08/20/09 5,436,096.3 236.1 1,840.0 289.5 24 60.00 0.234 0.001

0.3

08/20/09 5,437,300.6 238.1 1,840.0 286.6 24 60.00 0.355 0.002

0.6

08/20/09 5,474,818.3 241.8 1,840.0 288.6 24 60.00 0.355 0.002

1.5

08/19/09 5,497,483.0 252.5 1,840.0 283.8 24 60.00 0.725 0.003

1.8

08/19/09 6,496,367.7 270.1 1,840.0 331.9 30 60.00 1.832 0.010

1.6

08/19/09 9,658,898.3 275.8 1,840.0 561.7 50 60.00 1.931 0.017

1.7

08/19/09 9,628,260.7 275.1 1,840.0 565.1 50 60.00 1.701 0.015

1.8

08/19/09 9,641,190.5 274.0 1,840.0 560.6 50 60.00 1.824 0.016

1.7

08/19/09 9,585,627.5 272.1 1,840.0 562.7 50 60.00 1.914 0.017

1.5

08/19/09 9,576,716.5 271.7 1,840.0 562.1 50 60.00 1.807 0.016

1.5

08/19/09 9,643,267.2 272.8 1,840.0 566.0 50 60.00 1.595 0.014

1.6

08/19/09 9,560,079.3 271.6 1,840.0 566.3 50 60.00 1.580 0.014

1.4

08/19/09 9,688,185.1 269.0 1,840.0 558.1 50 60.00 1.733 0.015

1.3

08/19/09 9,517,981.9 268.8 1,840.0 548.3 50 60.00 1.516 0.013

1.1

08/19/09 9,478,334.6 271.0 1,840.0 546.0 50 60.00 1.408 0.012

1.5

08/19/09 9,406,100.2 274.2 1,840.0 547.0 50 60.00 1.180 0.010

1.5

08/19/09 9,540,738.8 274.8 1,840.0 554.8 50 60.00 1.610 0.014

1.4

08/19/09 9,602,359.8 273.4 1,840.0 558.4 50 60.00 1.610 0.014

1.4

08/19/09 9,637,845.0 273.2 1,840.0 560.5 50 60.00 1.502 0.013

1.2

08/19/09 9,699,128.0 266.6 1,840.0 564.0 50 60.00 1.502 0.014

1.7

08/19/09 9,057,155.0 244.8 1,840.0 526.7 46 60.00 1.288 0.011

1.3

08/19/09 5,839,084.9 236.1 1,840.0 285.6 24 60.00 2.169 0.010

1.3

08/19/09 5,841,452.2 238.8 1,840.0 285.7 24 60.00 1.658 0.008

1.3

08/19/09 5,885,126.1 241.2 1,840.0 284.7 24 60.00 1.677 0.008

1.3

08/19/09 5,897,999.9 242.9 1,840.0 285.3 24 60.00 1.677 0.008

0.9

08/19/09 5,846,167.0 246.1 1,840.0 285.9 24 60.00 1.658 0.008

1.6

08/19/09 5,486,080.7 254.5 1,840.0 283.2 24 60.00 1.088 0.005

1.8

08/18/09 5,660,530.6 269.1 1,840.0 283.0 25 60.00 1.997 0.009

1.8

08/18/09 9,468,256.0 277.5 1,840.0 540.3 48 60.00 1.968 0.017

1.7

08/18/09 9,729,035.2 278.9 1,840.0 560.5 50 60.00 1.950 0.017

1.6

08/18/09 9,719,153.1 280.8 1,840.0 559.9 50 60.00 1.841 0.016

1.7

08/18/09 9,775,180.9 281.7 1,840.0 563.1 50 60.00 1.733 0.016

1.6

08/18/09 9,747,752.0 281.8 1,840.0 561.6 50 60.00 1.841 0.017

08/18/09 9,748,883.8 282.9 1,840.0 556.3 50 60.00 1.750 0.016
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 S S SC

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00 1.2

1.1

08/21/09 5,584,194.1 242.1 1,840.0 258.0 22 60.00 1.621 0.007

1.4

08/21/09 5,792,742.1 248.7 1,840.0 261.3 22 60.00 1.522 0.006

2.0

08/21/09 5,738,031.4 262.4 1,840.0 268.2 23 60.00 1.869 0.008

2.1

08/21/09 7,937,825.5 280.0 1,840.0 396.9 36 60.00 2.496 0.016

1.8

08/21/09 9,935,439.6 283.0 1,840.0 561.5 50 60.00 2.318 0.021

1.6

08/21/09 9,953,589.8 280.7 1,840.0 562.6 50 60.00 1.987 0.018

1.7

08/21/09 9,862,156.6 275.9 1,840.0 557.4 50 60.00 1.766 0.016

0.9

08/21/09 9,793,726.9 269.4 1,840.0 553.6 50 60.00 1.877 0.017

0.6

08/21/09 9,328,679.3 251.9 1,840.0 527.3 47 60.00 0.994 0.008

1.0

08/21/09 5,807,437.8 241.1 1,840.0 299.8 26 60.00 0.725 0.003

0.9

08/21/09 5,724,847.2 241.7 1,840.0 286.3 25 60.00 1.248 0.006

0.9

08/21/09 6,112,335.5 240.1 1,840.0 302.3 26 60.00 1.136 0.005

1.3

08/21/09 6,007,829.5 238.3 1,840.0 297.1 25 60.00 1.136 0.005

1.0

08/21/09 5,751,580.2 237.3 1,840.0 287.6 24 60.00 1.622 0.007

1.0

08/21/09 5,700,234.1 239.3 1,840.0 281.9 24 60.00 1.262 0.006

1.0

08/21/09 5,826,666.0 240.7 1,840.0 278.7 24 60.00 1.305 0.006

0.7

08/21/09 5,876,705.0 239.6 1,840.0 284.3 24 60.00 1.290 0.006

1.2

08/21/09 5,814,240.2 238.3 1,840.0 287.5 24 60.00 0.883 0.004

0.9

08/21/09 5,790,752.2 236.6 1,840.0 289.5 24 60.00 1.498 0.007

0.4

08/20/09 5,765,312.9 235.1 1,840.0 288.3 24 60.00 1.123 0.005

0.4

08/20/09 5,673,214.8 237.4 1,840.0 280.6 24 60.00 0.505 0.002

0.6

08/20/09 5,665,685.4 243.2 1,840.0 280.2 24 60.00 0.505 0.002

1.1

08/20/09 5,742,756.0 254.0 1,840.0 277.8 24 60.00 0.774 0.003

0.7

08/20/09 8,574,688.6 263.6 1,840.0 438.1 41 60.00 1.344 0.009

0.4

08/20/09 9,884,573.2 249.9 1,840.0 564.1 50 60.00 0.765 0.007

0.3

08/20/09 6,150,145.6 236.5 1,840.0 327.6 28 60.00 0.469 0.002

0.3

08/20/09 5,725,407.3 238.2 1,840.0 292.5 25 60.00 0.366 0.002

0.4

08/20/09 5,767,187.5 238.0 1,840.0 291.5 25 60.00 0.370 0.002

0.6

08/20/09 5,709,453.6 238.1 1,840.0 288.6 25 60.00 0.494 0.002

0.6

08/20/09 5,664,559.4 240.3 1,840.0 286.3 25 60.00 0.741 0.003

0.4

08/20/09 5,772,650.9 241.0 1,840.0 307.5 25 60.00 0.703 0.003

0.3

08/20/09 5,808,557.3 238.9 1,840.0 312.5 25 60.00 0.464 0.002

0.5

08/20/09 5,819,601.2 236.4 1,840.0 329.0 25 60.00 0.331 0.002

0.5

08/20/09 5,754,345.8 234.5 1,840.0 319.0 25 60.00 0.563 0.003

0.4

08/20/09 5,774,632.9 233.9 1,840.0 310.7 25 60.00 0.580 0.003

0.2

08/20/09 5,793,336.3 233.7 1,840.0 299.1 25 60.00 0.483 0.002

08/20/09 5,623,251.3 234.0 1,840.0 299.5 25 60.00 0.234 0.001
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 S S SC

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 S S SC

05:00 C C

06:00

07:00 2.3

2.4

08/23/09 5,907,767.4 236.1 1,840.0 285.8 23 60.00 2.967 0.014

2.3

08/23/09 5,830,797.3 234.1 1,840.0 278.9 21 60.00 3.131 0.014

2.1

08/23/09 5,730,330.7 233.3 1,840.0 267.8 21 60.00 3.071 0.013

2.1

08/23/09 5,734,111.9 233.8 1,840.0 268.0 22 60.00 2.804 0.012

2.1

08/23/09 5,741,610.0 235.4 1,840.0 268.4 22 60.00 2.804 0.012

1.8

08/23/09 5,785,663.5 237.8 1,840.0 267.3 22 60.00 2.837 0.012

2.0

08/23/09 5,797,739.4 237.9 1,840.0 274.1 22 60.00 2.376 0.010

1.9

08/23/09 5,867,581.5 237.0 1,840.0 274.3 22 60.00 2.670 0.012

2.9

08/22/09 5,836,905.5 235.2 1,840.0 272.8 22 60.00 2.537 0.011

2.4

08/22/09 5,793,836.9 234.2 1,840.0 270.8 22 60.00 3.872 0.017

2.1

08/22/09 5,685,627.7 235.4 1,840.0 268.8 22 60.00 3.167 0.014

2.1

08/22/09 5,899,906.0 237.4 1,840.0 269.3 22 60.00 2.870 0.012

2.0

08/22/09 5,922,984.5 237.4 1,840.0 270.4 22 60.00 2.870 0.012

1.8

08/22/09 5,932,612.8 237.1 1,840.0 270.9 22 60.00 2.734 0.012

1.8

08/22/09 5,988,054.2 237.2 1,840.0 273.4 22 60.00 2.460 0.011

1.9

08/22/09 6,009,900.5 238.8 1,840.0 271.1 22 60.00 2.490 0.011

1.8

08/22/09 6,032,333.2 238.8 1,840.0 275.4 23 60.00 2.597 0.011

1.4

08/22/09 6,006,039.4 237.7 1,840.0 277.5 23 60.00 2.431 0.011

1.5

08/22/09 5,996,225.5 236.5 1,840.0 273.7 22 60.00 1.914 0.008

1.6

08/22/09 5,905,998.3 236.2 1,840.0 276.0 23 60.00 2.003 0.009

1.5

08/22/09 5,796,489.7 238.3 1,840.0 270.9 23 60.00 2.136 0.009

1.4

08/22/09 5,806,848.5 238.2 1,840.0 271.4 23 60.00 2.003 0.009

1.2

08/22/09 5,931,163.3 237.1 1,840.0 270.8 23 60.00 1.914 0.008

1.5

08/22/09 5,854,672.7 234.8 1,840.0 273.7 23 60.00 1.602 0.007

1.8

08/22/09 5,837,069.0 232.5 1,840.0 272.8 23 60.00 2.003 0.009

1.7

08/22/09 5,828,720.3 231.2 1,840.0 259.8 21 60.00 2.520 0.010

1.4

08/22/09 5,663,334.5 232.1 1,840.0 252.4 21 60.00 2.380 0.010

1.1

08/22/09 5,655,012.5 233.9 1,840.0 252.0 21 60.00 1.960 0.008

1.1

08/22/09 5,689,340.1 233.4 1,840.0 250.4 21 60.00 1.559 0.006

1.1

08/22/09 5,610,733.2 232.2 1,840.0 250.1 21 60.00 1.540 0.006

1.4

08/22/09 5,715,388.5 231.6 1,840.0 254.7 21 60.00 1.540 0.006

1.3

08/22/09 5,551,182.7 232.8 1,840.0 253.4 21 60.00 1.914 0.008

1.4

08/21/09 5,590,509.0 234.6 1,840.0 252.2 21 60.00 1.798 0.007

1.4

08/21/09 5,618,792.1 234.9 1,840.0 253.5 21 60.00 1.937 0.008

1.1

08/21/09 5,625,885.3 234.9 1,840.0 253.8 21 60.00 1.937 0.008

1.3

08/21/09 5,737,907.3 235.5 1,840.0 258.8 21 60.00 1.522 0.006

08/21/09 5,540,981.4 238.4 1,840.0 259.0 22 60.00 1.736 0.007
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 S S SC

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00 S S S

20:00 S S 1.6 S

1.6

08/24/09 10,046,330.5 276.8 1,840.0 606.0 54 60.00 1.655 0.016

2.0

08/24/09 10,259,697.4 277.5 1,840.0 613.4 55 60.00 1.670 0.016

1.8

08/24/09 10,191,567.2 276.3 1,840.0 609.3 55 60.00 2.088 0.020

1.7

08/24/09 10,222,416.2 278.0 1,840.0 611.1 55 60.00 1.879 0.018

1.8

08/24/09 10,189,916.4 279.8 1,840.0 609.2 55 60.00 1.774 0.017

1.9

08/24/09 10,191,334.4 281.1 1,840.0 609.2 55 60.00 1.879 0.018

2.0

08/24/09 10,227,513.6 281.7 1,840.0 611.5 55 60.00 1.983 0.019

2.0

08/24/09 10,280,731.0 283.7 1,840.0 614.6 55 60.00 2.088 0.021

1.9

08/24/09 10,245,219.5 286.6 1,840.0 618.0 55 60.00 2.069 0.020

1.9

08/24/09 10,462,517.9 285.3 1,840.0 631.2 55 60.00 1.965 0.020

1.5

08/24/09 10,502,830.0 278.6 1,840.0 633.6 55 60.00 1.965 0.020

1.4

08/24/09 10,118,908.2 257.6 1,840.0 588.4 50 60.00 1.610 0.015

1.3

08/24/09 6,264,080.6 242.7 1,840.0 320.0 27 60.00 1.710 0.009

0.8

08/24/09 6,054,659.4 239.9 1,840.0 302.8 25 60.00 1.622 0.008

1.2

08/24/09 6,032,779.5 238.9 1,840.0 298.4 25 60.00 1.009 0.005

1.3

08/24/09 6,071,304.8 238.9 1,840.0 283.8 23 60.00 1.602 0.007

1.4

08/24/09 5,916,921.3 238.1 1,840.0 270.1 22 60.00 1.777 0.008

1.4

08/24/09 5,900,135.1 236.7 1,840.0 269.3 22 60.00 1.914 0.008

1.8

08/24/09 5,880,933.9 234.6 1,840.0 278.1 22 60.00 1.848 0.008

1.6

08/24/09 5,793,529.6 233.8 1,840.0 270.8 22 60.00 2.403 0.010

1.0

08/24/09 5,750,691.8 235.4 1,840.0 268.8 22 60.00 2.136 0.009

1.1

08/23/09 5,824,195.2 238.8 1,840.0 265.9 22 60.00 1.367 0.006

1.2

08/23/09 5,785,724.4 240.4 1,840.0 270.4 22 60.00 1.469 0.006

1.2

08/23/09 5,792,704.2 243.3 1,840.0 270.8 22 60.00 1.602 0.007

2.3

08/23/09 5,764,263.5 250.7 1,840.0 266.3 22 60.00 1.621 0.007

2.0

08/23/09 5,835,986.0 263.3 1,840.0 263.3 22 60.00 3.182 0.013

2.2

08/23/09 8,714,052.4 275.2 1,840.0 478.3 43 60.00 2.274 0.017

1.9

08/23/09 9,924,322.0 275.4 1,840.0 577.1 50 60.00 2.361 0.022

1.3

08/23/09 10,028,149.2 268.5 1,840.0 577.7 50 60.00 2.058 0.019

1.3

08/23/09 8,358,689.8 246.5 1,840.0 458.8 39 60.00 1.478 0.011

1.4

08/23/09 5,916,572.6 239.5 1,840.0 286.2 24 60.00 1.677 0.008

2.3

08/23/09 6,008,149.1 238.3 1,840.0 287.3 24 60.00 1.827 0.008

2.0

08/23/09 5,822,759.8 238.3 1,840.0 284.8 22 60.00 2.934 0.013

2.0

08/23/09 5,977,682.2 241.3 1,840.0 285.9 23 60.00 2.609 0.012

2.0

08/23/09 6,104,849.0 242.3 1,840.0 288.7 23 60.00 2.639 0.012

1.7

08/23/09 6,081,049.3 241.0 1,840.0 287.5 23 60.00 2.639 0.012

08/23/09 6,015,176.1 238.9 1,840.0 287.7 23 60.00 2.218 0.010
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 S S SC

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 S S SC

02:00 C C

03:00

04:00 S S SC

05:00 C C

06:00

07:00

08:00

09:00 1.1

1.0

08/26/09 5,658,536.7 240.2 1,840.0 276.8 22 60.00 1.403 0.006

0.9

08/26/09 5,667,917.8 239.0 1,840.0 277.2 22 60.00 1.276 0.006

1.5

08/26/09 5,669,003.1 237.3 1,840.0 277.3 22 60.00 1.148 0.005

1.5

08/26/09 5,571,509.5 236.0 1,840.0 275.6 22 60.00 1.893 0.008

1.3

08/26/09 5,577,585.6 236.6 1,840.0 275.9 22 60.00 1.893 0.008

1.1

08/26/09 5,606,578.6 238.5 1,840.0 274.3 22 60.00 1.658 0.007

1.1

08/26/09 5,608,977.6 239.2 1,840.0 271.3 22 60.00 1.419 0.006

1.1

08/26/09 5,650,376.2 240.0 1,840.0 267.1 22 60.00 1.452 0.006

1.0

08/26/09 5,667,501.1 241.5 1,840.0 277.2 22 60.00 1.403 0.006

1.2

08/26/09 5,667,485.3 245.1 1,840.0 274.1 22 60.00 1.290 0.006

1.3

08/25/09 5,712,455.2 249.4 1,840.0 276.3 22 60.00 1.548 0.007

1.6

08/25/09 5,723,781.4 258.0 1,840.0 273.8 22 60.00 1.696 0.007

1.5

08/25/09 6,786,881.7 271.7 1,840.0 324.6 28 60.00 2.088 0.011

1.4

08/25/09 10,166,414.6 276.9 1,840.0 607.8 55 60.00 1.566 0.015

1.3

08/25/09 10,184,269.6 279.3 1,840.0 603.3 55 60.00 1.475 0.014

1.3

08/25/09 10,460,202.4 282.2 1,840.0 619.6 56 60.00 1.369 0.014

1.4

08/25/09 10,147,320.7 279.6 1,840.0 590.1 52 60.00 1.395 0.013

1.4

08/25/09 9,922,343.9 276.4 1,840.0 577.0 50 60.00 1.502 0.014

0.9

08/25/09 9,922,637.9 270.6 1,840.0 577.0 50 60.00 1.502 0.014

1.1

08/25/09 9,669,346.5 255.6 1,840.0 557.0 47 60.00 0.975 0.009

1.1

08/25/09 6,094,822.0 241.0 1,840.0 314.7 25 60.00 1.329 0.007

1.0

08/25/09 5,676,474.3 238.5 1,840.0 277.6 22 60.00 1.403 0.006

1.6

08/25/09 5,643,692.0 236.2 1,840.0 276.1 22 60.00 1.276 0.006

1.1

08/25/09 5,612,630.0 234.7 1,840.0 274.5 22 60.00 2.041 0.009

0.8

08/25/09 5,588,069.5 234.4 1,840.0 273.3 22 60.00 1.403 0.006

0.5

08/25/09 5,613,502.3 234.1 1,840.0 271.5 22 60.00 1.032 0.004

0.5

08/25/09 5,499,306.9 231.6 1,840.0 274.9 22 60.00 0.624 0.003

0.6

08/25/09 5,339,651.7 230.5 1,840.0 269.9 22 60.00 0.617 0.003

0.6

08/25/09 5,298,482.5 229.9 1,840.0 270.7 22 60.00 0.733 0.003

0.6

08/25/09 5,264,113.8 231.4 1,840.0 268.9 22 60.00 0.733 0.003

0.6

08/25/09 5,282,712.6 233.9 1,840.0 267.0 22 60.00 0.741 0.003

0.6

08/25/09 5,327,515.6 234.0 1,840.0 269.3 22 60.00 0.741 0.003

0.6

08/25/09 5,313,249.8 234.2 1,840.0 271.4 22 60.00 0.733 0.003

0.7

08/25/09 5,364,296.8 235.6 1,840.0 271.1 22 60.00 0.741 0.003

1.0

08/24/09 5,323,671.0 240.4 1,840.0 272.0 22 60.00 0.855 0.004

1.3

08/24/09 5,338,427.8 251.1 1,840.0 269.8 22 60.00 1.235 0.005

08/24/09 6,270,853.2 266.8 1,840.0 310.1 28 60.00 1.640 0.008
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 S S SC

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00 2.0

1.6

08/27/09 5,801,473.5 267.9 1,840.0 280.6 23 60.00 2.580 0.012

1.5

08/27/09 8,573,009.9 280.9 1,840.0 475.2 42 60.00 1.801 0.014

1.5

08/27/09 9,938,171.6 283.7 1,840.0 588.7 51 60.00 1.580 0.015

1.6

08/27/09 9,873,494.5 284.3 1,840.0 584.9 51 60.00 1.580 0.015

1.7

08/27/09 9,863,277.0 283.8 1,840.0 584.3 50 60.00 1.685 0.016

1.6

08/27/09 9,856,972.3 281.7 1,840.0 583.9 51 60.00 1.791 0.017

1.6

08/27/09 9,826,830.0 282.0 1,840.0 576.8 50 60.00 1.701 0.016

1.7

08/27/09 9,767,655.9 282.9 1,840.0 578.6 50 60.00 1.685 0.016

1.6

08/27/09 9,848,528.1 282.8 1,840.0 578.1 50 60.00 1.807 0.017

1.8

08/27/09 9,812,441.5 281.5 1,840.0 581.3 50 60.00 1.685 0.016

1.6

08/27/09 9,790,158.3 282.0 1,840.0 580.0 50 60.00 1.896 0.018

1.7

08/27/09 9,795,054.9 281.9 1,840.0 580.2 50 60.00 1.685 0.016

1.9

08/27/09 9,833,172.1 279.9 1,840.0 582.5 50 60.00 1.791 0.017

1.5

08/27/09 9,857,180.4 273.0 1,840.0 583.9 50 60.00 2.001 0.019

2.5

08/27/09 9,543,197.8 254.0 1,840.0 565.3 48 60.00 1.580 0.014

2.3

08/27/09 5,922,096.5 241.3 1,840.0 292.9 23 60.00 3.154 0.015

2.3

08/27/09 5,717,426.9 240.2 1,840.0 276.5 22 60.00 2.967 0.013

2.1

08/27/09 5,754,987.2 239.8 1,840.0 275.2 22 60.00 3.001 0.013

2.1

08/27/09 5,737,180.3 241.2 1,840.0 274.4 22 60.00 2.740 0.012

2.1

08/27/09 5,858,601.7 241.8 1,840.0 273.8 22 60.00 2.804 0.012

1.9

08/27/09 5,886,693.7 241.9 1,840.0 272.0 22 60.00 2.837 0.012

2.5

08/27/09 5,925,946.1 243.2 1,840.0 277.0 22 60.00 2.537 0.011

2.0

08/27/09 5,873,832.8 247.6 1,840.0 280.9 23 60.00 3.262 0.015

1.6

08/26/09 6,034,011.0 258.5 1,840.0 282.0 23 60.00 2.670 0.012

1.7

08/26/09 6,791,353.0 274.4 1,840.0 324.8 28 60.00 2.088 0.011

1.8

08/26/09 9,818,979.8 280.7 1,840.0 576.3 50 60.00 1.807 0.017

1.9

08/26/09 9,834,750.3 278.9 1,840.0 577.3 50 60.00 1.914 0.018

1.6

08/26/09 9,777,222.5 277.3 1,840.0 573.9 50 60.00 2.020 0.019

1.6

08/26/09 9,823,159.9 277.5 1,840.0 576.6 50 60.00 1.701 0.016

1.1

08/26/09 9,852,530.8 273.4 1,840.0 578.3 50 60.00 1.701 0.016

1.2

08/26/09 10,009,150.1 258.1 1,840.0 587.5 50 60.00 1.169 0.011

1.6

08/26/09 6,458,802.9 239.4 1,840.0 340.5 28 60.00 1.420 0.008

1.6

08/26/09 5,654,961.6 240.2 1,840.0 276.6 22 60.00 2.041 0.009

1.4

08/26/09 5,687,806.9 240.3 1,840.0 278.2 22 60.00 2.041 0.009

1.1

08/26/09 5,736,957.8 239.5 1,840.0 280.6 22 60.00 1.786 0.008

1.1

08/26/09 5,705,789.1 239.1 1,840.0 279.1 22 60.00 1.403 0.006

08/26/09 5,633,371.5 240.4 1,840.0 275.5 22 60.00 1.403 0.006
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

23:00

00:00

01:00

02:00 C

03:00

04:00 S S SC

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 S S SC

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00 0.6

0.6

08/29/09 5,619,471.0 238.9 1,840.0 293.2 24 60.00 0.718 0.003

0.6

08/29/09 5,592,473.5 239.4 1,840.0 291.8 24 60.00 0.718 0.003

0.5

08/29/09 5,575,410.9 239.4 1,840.0 293.9 24 60.00 0.710 0.003

0.5

08/29/09 5,576,115.3 238.8 1,840.0 290.9 24 60.00 0.598 0.003

0.6

08/29/09 5,608,734.9 238.8 1,840.0 292.6 24 60.00 0.598 0.003

0.7

08/29/09 5,566,219.7 240.1 1,840.0 287.4 24 60.00 0.725 0.003

0.9

08/29/09 5,646,659.9 240.1 1,840.0 291.6 24 60.00 0.846 0.004

0.9

08/29/09 5,697,390.3 239.6 1,840.0 291.0 24 60.00 1.099 0.005

0.9

08/29/09 5,716,378.1 238.8 1,840.0 288.9 24 60.00 1.111 0.005

1.2

08/29/09 5,645,853.7 238.2 1,840.0 288.4 24 60.00 1.099 0.005

1.1

08/29/09 5,638,121.7 239.0 1,840.0 291.1 24 60.00 1.450 0.007

1.1

08/29/09 5,839,167.0 242.0 1,840.0 291.9 24 60.00 1.373 0.006

1.0

08/28/09 5,883,176.1 244.6 1,840.0 291.0 24 60.00 1.388 0.006

0.9

08/28/09 5,911,567.5 246.1 1,840.0 295.6 24 60.00 1.248 0.006

0.9

08/28/09 5,911,123.9 248.8 1,840.0 298.8 24 60.00 1.111 0.005

1.2

08/28/09 5,864,432.8 255.6 1,840.0 293.2 24 60.00 1.123 0.005

1.4

08/28/09 5,909,364.3 268.1 1,840.0 292.2 24 60.00 1.514 0.007

1.5

08/28/09 7,771,121.3 285.3 1,840.0 401.2 36 60.00 1.692 0.011

1.8

08/28/09 9,964,828.3 288.0 1,840.0 574.1 50 60.00 1.625 0.015

1.6

08/28/09 9,947,688.8 286.4 1,840.0 573.1 50 60.00 1.950 0.018

1.7

08/28/09 9,957,280.7 288.3 1,840.0 568.2 50 60.00 1.750 0.016

1.5

08/28/09 9,994,090.8 289.3 1,840.0 570.3 50 60.00 1.859 0.017

1.5

08/28/09 10,041,884.9 290.1 1,840.0 573.0 50 60.00 1.640 0.015

2.2

08/28/09 9,927,380.4 296.3 1,840.0 566.5 50 60.00 1.640 0.015

2.6

08/28/09 12,150,692.7 316.1 1,840.0 733.0 65 60.00 2.276 0.027

2.4

08/28/09 13,972,660.2 319.0 1,840.0 865.7 75 60.00 2.619 0.036

1.8

08/28/09 13,726,493.5 309.3 1,840.0 850.4 75 60.00 2.417 0.033

1.4

08/28/09 12,149,510.3 288.2 1,840.0 746.2 65 60.00 1.829 0.022

0.9

08/28/09 9,898,927.0 274.3 1,840.0 570.3 50 60.00 1.516 0.014

1.3

08/28/09 8,635,242.8 253.6 1,840.0 502.1 42 60.00 0.966 0.008

1.6

08/28/09 5,725,396.4 245.9 1,840.0 283.1 23 60.00 1.640 0.007

1.8

08/28/09 5,753,698.2 244.9 1,840.0 281.4 23 60.00 2.041 0.009

1.8

08/28/09 5,676,896.6 244.4 1,840.0 280.8 23 60.00 2.271 0.010

1.8

08/28/09 5,632,554.7 244.9 1,840.0 275.5 23 60.00 2.296 0.010

1.8

08/28/09 5,691,258.7 245.9 1,840.0 284.5 23 60.00 2.246 0.010

1.8

08/28/09 5,699,106.4 248.6 1,840.0 281.9 23 60.00 2.271 0.010

08/27/09 5,730,322.3 254.8 1,840.0 283.4 23 60.00 2.271 0.010
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 S S SC

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00 0.8

0.7

08/31/09 5,704,601.5 238.3 1,840.0 297.7 24 60.00 0.957 0.005

0.8

08/30/09 5,654,219.0 239.4 1,840.0 295.0 24 60.00 0.837 0.004

0.9

08/30/09 5,637,522.8 245.4 1,840.0 294.2 24 60.00 0.957 0.005

1.2

08/30/09 5,657,486.7 256.0 1,840.0 292.1 24 60.00 1.088 0.005

1.3

08/30/09 6,313,660.1 271.3 1,840.0 326.0 28 60.00 1.450 0.008

1.1

08/30/09 9,871,738.0 276.6 1,840.0 579.4 50 60.00 1.382 0.013

0.6

08/30/09 9,833,048.1 270.6 1,840.0 582.5 50 60.00 1.159 0.011

0.8

08/30/09 9,718,004.7 252.1 1,840.0 570.4 48 60.00 0.638 0.006

0.9

08/30/09 5,612,478.9 236.4 1,840.0 289.8 23 60.00 0.967 0.004

1.2

08/30/09 5,428,605.4 234.7 1,840.0 274.4 22 60.00 1.111 0.005

1.2

08/30/09 5,424,912.3 233.4 1,840.0 274.2 22 60.00 1.481 0.006

0.8

08/30/09 5,385,781.3 234.7 1,840.0 272.2 22 60.00 1.481 0.006

0.7

08/30/09 5,435,589.9 237.0 1,840.0 271.8 22 60.00 0.998 0.004

0.8

08/30/09 5,445,420.7 237.0 1,840.0 275.2 22 60.00 0.864 0.004

0.9

08/30/09 5,448,450.0 235.9 1,840.0 275.4 22 60.00 0.988 0.004

1.2

08/30/09 5,445,653.0 234.1 1,840.0 272.3 22 60.00 1.123 0.005

1.2

08/30/09 5,365,797.5 232.4 1,840.0 271.2 22 60.00 1.481 0.006

1.0

08/30/09 5,340,300.8 231.2 1,840.0 269.9 22 60.00 1.481 0.006

1.0

08/30/09 5,330,395.8 231.1 1,840.0 269.4 22 60.00 1.235 0.005

0.9

08/30/09 5,345,928.4 232.7 1,840.0 270.2 22 60.00 1.235 0.005

0.7

08/30/09 5,390,547.5 235.2 1,840.0 269.6 22 60.00 1.123 0.005

0.8

08/30/09 5,437,207.7 236.2 1,840.0 268.9 22 60.00 0.883 0.004

0.7

08/30/09 5,430,346.8 236.9 1,840.0 268.5 22 60.00 1.009 0.004

1.0

08/30/09 5,418,208.5 238.2 1,840.0 270.9 22 60.00 0.874 0.004

0.7

08/30/09 5,441,318.2 242.6 1,840.0 278.0 22 60.00 1.221 0.005

1.1

08/29/09 5,548,830.4 252.1 1,840.0 283.5 23 60.00 0.855 0.004

1.0

08/29/09 5,834,700.5 266.2 1,840.0 285.4 24 60.00 1.403 0.006

0.9

08/29/09 9,456,812.2 275.1 1,840.0 534.5 48 60.00 1.104 0.009

0.8

08/29/09 9,581,538.2 273.7 1,840.0 557.2 50 60.00 0.966 0.009

0.5

08/29/09 9,997,215.3 261.2 1,840.0 581.3 50 60.00 0.858 0.008

0.5

08/29/09 7,010,550.7 241.0 1,840.0 388.7 32 60.00 0.563 0.003

0.5

08/29/09 5,529,470.5 239.6 1,840.0 294.5 24 60.00 0.586 0.003

0.5

08/29/09 5,555,270.7 239.5 1,840.0 292.8 24 60.00 0.592 0.003

0.6

08/29/09 5,622,344.6 239.0 1,840.0 293.3 24 60.00 0.598 0.003

0.6

08/29/09 5,604,234.6 239.5 1,840.0 292.4 24 60.00 0.718 0.003

0.6

08/29/09 5,612,828.3 239.8 1,840.0 292.9 24 60.00 0.718 0.003

08/29/09 5,609,054.5 239.3 1,840.0 292.6 24 60.00 0.718 0.003
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

01:00

02:00 C S S S

03:00 S S S

04:00 S S SC

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 S S SC

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00 1.0

1.5

09/01/09 5,690,158.2 240.9 1,840.0 296.9 24 60.00 1.196 0.006

1.4

09/01/09 5,719,499.0 242.3 1,840.0 295.3 24 60.00 1.813 0.009

1.6

09/01/09 5,765,420.6 243.9 1,840.0 294.5 24 60.00 1.710 0.008

1.2

09/01/09 5,744,502.6 243.4 1,840.0 296.6 24 60.00 1.934 0.009

1.1

09/01/09 5,779,493.0 242.1 1,840.0 182.2 24 60.00 2.376 0.007

1.6

09/01/09 5,730,629.1 239.9 1,840.0 227.4 24 60.00 1.730 0.006

1.2

09/01/09 5,688,544.8 238.8 1,840.0 154.6 24 60.00 3.674 0.009

1.1

09/01/09 5,663,739.1 239.5 1,840.0 224.7 24 60.00 1.887 0.007

1.2

09/01/09 5,650,818.1 239.3 1,840.0 294.8 24 60.00 1.316 0.006

1.3

09/01/09 5,666,116.5 238.7 1,840.0 292.5 24 60.00 1.450 0.007

1.3

09/01/09 5,668,527.6 238.6 1,840.0 292.7 24 60.00 1.571 0.007

1.1

09/01/09 5,710,777.0 239.9 1,840.0 301.1 24 60.00 1.539 0.007

1.0

09/01/09 5,641,545.0 240.1 1,840.0 294.4 24 60.00 1.316 0.006

0.7

09/01/09 5,656,760.3 239.9 1,840.0 295.1 24 60.00 1.196 0.006

0.7

08/31/09 5,694,003.9 240.6 1,840.0 294.0 24 60.00 0.846 0.004

0.8

08/31/09 5,668,097.8 242.7 1,840.0 292.6 24 60.00 0.846 0.004

0.8

08/31/09 5,637,519.7 245.3 1,840.0 294.2 24 60.00 0.957 0.005

0.9

08/31/09 5,705,424.6 249.0 1,840.0 297.7 24 60.00 0.957 0.005

1.4

08/31/09 5,712,383.2 258.8 1,840.0 294.9 24 60.00 1.088 0.005

1.5

08/31/09 7,477,768.2 276.2 1,840.0 386.1 34 60.00 1.692 0.010

1.4

08/31/09 9,771,656.7 280.4 1,840.0 573.6 50 60.00 1.595 0.015

1.4

08/31/09 9,755,754.0 280.4 1,840.0 572.6 50 60.00 1.488 0.014

1.7

08/31/09 9,749,497.8 280.0 1,840.0 572.2 50 60.00 1.488 0.014

1.9

08/31/09 9,807,089.5 278.4 1,840.0 575.6 50 60.00 1.807 0.017

1.9

08/31/09 9,787,787.2 279.2 1,840.0 574.5 50 60.00 2.020 0.019

1.8

08/31/09 9,801,004.0 279.2 1,840.0 575.3 50 60.00 2.020 0.019

1.7

08/31/09 9,835,996.6 277.7 1,840.0 577.3 50 60.00 1.914 0.018

1.4

08/31/09 9,815,398.2 274.0 1,840.0 576.1 50 60.00 1.807 0.017

0.6

08/31/09 9,824,093.7 264.6 1,840.0 576.6 50 60.00 1.488 0.014

0.6

08/31/09 8,463,353.3 243.6 1,840.0 482.9 41 60.00 0.656 0.005

0.6

08/31/09 5,662,413.4 236.0 1,840.0 292.3 24 60.00 0.725 0.003

0.7

08/31/09 5,632,287.1 235.6 1,840.0 290.8 24 60.00 0.725 0.003

0.7

08/31/09 5,639,828.9 236.4 1,840.0 291.2 24 60.00 0.846 0.004

0.7

08/31/09 5,653,395.2 235.9 1,840.0 291.9 24 60.00 0.846 0.004

0.7

08/31/09 5,626,772.7 235.4 1,840.0 290.5 24 60.00 0.846 0.004

0.8

08/31/09 5,615,284.3 237.8 1,840.0 289.9 24 60.00 0.846 0.004

08/31/09 5,647,601.3 238.1 1,840.0 291.6 24 60.00 0.967 0.005
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00 S S SC

02:00 C S S SC

03:00 S S S

04:00 S S SC

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00 MC M

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C 2.0

2.0

09/03/09 5,605,159.6 242.4 1,840.0 289.4 24 60.00 2.417 0.011

2.4

09/03/09 5,684,622.3 242.3 1,840.0 299.7 24 60.00 2.367 0.011

2.3

09/03/09 5,701,770.0 243.5 1,840.0 300.6 24 60.00 2.841 0.014

1.9

09/02/09 5,648,252.8 247.6 1,840.0 294.7 24 60.00 2.751 0.013

1.9

09/02/09 5,680,996.2 257.4 1,840.0 293.3 24 60.00 2.296 0.011

2.2

09/02/09 5,821,604.8 272.8 1,840.0 291.1 24 60.00 2.371 0.011

2.2

09/02/09 9,292,688.5 284.3 1,840.0 540.4 47 60.00 2.361 0.020

1.9

09/02/09 9,938,587.2 284.4 1,840.0 594.2 52 60.00 2.296 0.022

2.2

09/02/09 9,909,944.1 283.7 1,840.0 597.8 52 60.00 1.965 0.019

1.7

09/02/09 9,937,157.5 283.8 1,840.0 599.5 52 60.00 2.276 0.022

1.4

09/02/09 9,931,387.0 285.0 1,840.0 599.1 52 60.00 1.758 0.017

1.4

09/02/09 9,890,359.2 285.7 1,840.0 596.6 52 60.00 1.448 0.014

1.4

09/02/09 9,918,084.4 285.6 1,840.0 598.3 52 60.00 1.448 0.014

1.5

09/02/09 9,907,978.2 284.2 1,840.0 597.7 52 60.00 1.448 0.014

1.5

09/02/09 9,891,761.8 282.7 1,840.0 596.7 52 60.00 1.552 0.015

1.4

09/02/09 9,908,458.7 281.3 1,840.0 597.7 52 60.00 1.552 0.015

1.4

09/02/09 9,908,152.8 282.2 1,840.0 597.7 52 60.00 1.448 0.014

1.3

09/02/09 9,876,363.3 281.9 1,840.0 595.8 52 60.00 1.448 0.014

1.0

09/02/09 9,933,917.6 279.1 1,840.0 599.3 52 60.00 1.345 0.013

0.7

09/02/09 9,904,247.9 268.9 1,840.0 597.5 52 60.00 1.034 0.010

1.1

09/02/09 8,529,628.6 242.7 1,840.0 505.3 42 60.00 0.737 0.006

0.9

09/02/09 5,543,998.9 236.1 1,840.0 295.3 24 60.00 1.289 0.006

0.9

09/02/09 5,585,206.7 237.7 1,840.0 294.4 24 60.00 1.065 0.005

0.9

09/02/09 5,584,312.6 237.6 1,840.0 294.4 24 60.00 1.065 0.005

0.9

09/02/09 5,566,447.1 237.2 1,840.0 287.4 24 60.00 1.088 0.005

0.8

09/02/09 5,587,836.7 237.8 1,840.0 294.6 24 60.00 1.065 0.005

0.9

09/02/09 5,583,752.0 238.9 1,840.0 294.4 24 60.00 0.947 0.004

0.9

09/01/09 5,609,028.6 238.9 1,840.0 295.7 24 60.00 1.065 0.005

0.8

09/01/09 5,624,350.9 238.7 1,840.0 296.5 24 60.00 1.065 0.005

0.9

09/01/09 5,611,323.5 239.9 1,840.0 295.8 24 60.00 0.947 0.004

0.9

09/01/09 5,609,814.8 240.9 1,840.0 295.7 24 60.00 1.065 0.005

0.9

09/01/09 5,619,497.4 240.8 1,840.0 296.2 24 60.00 1.065 0.005

0.8

09/01/09 5,604,710.8 240.6 1,840.0 295.5 24 60.00 1.065 0.005

0.9

09/01/09 5,610,394.9 241.6 1,840.0 292.7 24 60.00 0.957 0.004

0.9

09/01/09 5,672,979.4 242.7 1,840.0 296.0 24 60.00 1.076 0.005

0.9

09/01/09 5,647,270.3 242.5 1,840.0 294.6 24 60.00 1.076 0.005

09/01/09 5,671,353.9 241.8 1,840.0 295.9 24 60.00 1.076 0.005
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

03:00

04:00 S S SC

05:00 C C

06:00

07:00 C

08:00 C

09:00 C

10:00 C

11:00 C

12:00 C

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F FS FS

03:00 F F F F F F F FS FS

04:00 F F F FT F F FT F FC

05:00 FC F F FT F F FT F FC

06:00 F F F FT F F FT F F

07:00 F F F FT F F FT F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F 0.0 F

0.0

09/04/09 435,168.5 122.4 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 482,176.1 124.5 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 489,610.2 126.2 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 474,459.2 127.8 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 427,466.2 129.4 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 266,024.0 131.6 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 288,563.3 134.2 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 139,475.7 136.7 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 7,372.8 140.5 1,840.0 0 0.00 0.000

0.0

09/04/09 8,041.1 144.0 1,840.0 0 0.00 0.000

0.0

09/04/09 30,798.6 149.3 1,840.0 0 0.00 0.000

0.0

09/04/09 53,288.7 155.5 1,840.0 0 0.00 0.000

0.0

09/04/09 71,512.8 163.9 1,840.0 0 0.00 0.000

0.0

09/04/09 245,877.5 175.3 1,840.0 0 0.00 0.000

0.1

09/04/09 379,399.6 187.7 1,840.0 0 0.00 0.000

0.2

09/04/09 522,705.7 207.8 1,840.0 0 0.00 0.000

0.5

09/03/09 862,876.3 228.4 1,840.0 0 0.00 0.000

1.4

09/03/09 5,255,124.4 265.9 1,840.0 134.2 12 28.00 1.221 0.001

1.9

09/03/09 8,945,835.7 280.8 1,840.0 500.8 46 60.00 1.561 0.012

1.8

09/03/09 9,888,087.4 282.3 1,840.0 569.6 50 60.00 2.058 0.019

2.0

09/03/09 9,839,826.5 282.0 1,840.0 572.2 50 60.00 1.931 0.018

2.6

09/03/09 9,861,063.4 283.6 1,840.0 573.4 50 60.00 2.146 0.020

2.6

09/03/09 9,919,550.8 283.8 1,840.0 576.9 50 60.00 2.790 0.026

2.5

09/03/09 9,928,138.3 284.0 1,840.0 577.3 50 60.00 2.790 0.026

1.9

09/03/09 10,001,027.0 282.1 1,840.0 576.1 50 60.00 2.708 0.025

1.3

09/03/09 9,996,758.1 278.3 1,840.0 575.9 50 60.00 2.058 0.019

1.0

09/03/09 10,070,085.7 264.3 1,840.0 591.1 50 60.00 1.382 0.013

1.1

09/03/09 6,539,995.7 244.0 1,840.0 359.0 29 60.00 1.137 0.007

1.7

09/03/09 5,601,314.1 241.7 1,840.0 295.3 24 60.00 1.302 0.006

1.5

09/03/09 5,593,740.9 241.6 1,840.0 294.9 24 60.00 2.012 0.009

1.5

09/03/09 5,625,639.5 242.0 1,840.0 293.5 24 60.00 1.794 0.008

1.7

09/03/09 5,606,855.9 241.2 1,840.0 295.6 24 60.00 1.776 0.008

1.6

09/03/09 5,586,982.9 239.4 1,840.0 294.5 24 60.00 2.012 0.009

2.0

09/03/09 5,565,229.6 237.5 1,840.0 290.3 24 60.00 1.914 0.009

1.8

09/03/09 5,561,233.1 239.4 1,840.0 293.2 24 60.00 2.367 0.011

1.7

09/03/09 5,620,718.4 241.8 1,840.0 293.3 24 60.00 2.153 0.010

09/03/09 5,617,000.8 242.2 1,840.0 293.1 24 60.00 2.033 0.010
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F 2.5 FC

0.0

09/06/09 519,792.9 95.2 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 534,299.4 95.9 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 2,392,489.7 96.8 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 565,370.0 97.5 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 581,261.2 98.3 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 575,990.8 99.0 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 577,442.2 99.7 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 579,799.0 100.3 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 598,396.8 101.2 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 607,140.0 102.2 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 613,225.4 103.1 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 614,842.0 103.8 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 617,686.1 104.7 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 643,880.2 105.8 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 558,448.9 106.6 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 549,314.0 107.0 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 459,795.4 107.1 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 533,175.1 106.9 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 689,953.8 106.6 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 622,571.2 106.2 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 718,601.8 106.2 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 705,043.5 106.3 1,840.0 0.0 0 0.00 0.000

0.2

09/05/09 595,016.3 107.2 1,840.0 0.0 0 0.00 0.000

2.5

09/05/09 523,467.9 108.5 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 528,632.6 109.7 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 531,327.2 110.9 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 2,392,698.2 112.0 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 539,270.7 112.2 1,840.0 0.0 0 0.00 0.000

0.0

09/05/09 510,158.9 112.9 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 488,463.6 113.8 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 496,578.6 114.5 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 471,651.0 115.1 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 453,864.9 116.7 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 421,130.6 118.5 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 443,713.8 120.4 1,840.0 0.0 0 0.00 0.000

0.0

09/04/09 466,815.7 121.1 1,840.0 0.0 0 0.00 0.000

09/04/09 451,824.9 121.7 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F 0.0 F

0.0

09/07/09 298,704.9 86.9 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 316,381.6 87.2 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 288,234.9 87.5 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 277,100.9 87.7 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 298,642.7 87.7 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 284,571.7 87.4 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 246,002.9 87.0 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 240,979.1 86.4 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 247,243.4 85.6 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 315,371.8 85.2 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 361,897.1 84.8 1,840.0 0.0 0 0.00 0.000

0.2

09/07/09 437,220.3 84.9 1,840.0 0.0 0 0.00 0.000

2.4

09/07/09 454,742.5 85.4 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 451,309.9 86.0 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 461,563.5 86.7 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 2,327,103.9 87.3 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 428,000.1 88.0 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 445,759.9 88.6 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 442,808.7 89.2 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 428,052.8 89.8 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 440,161.0 90.3 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 459,548.2 91.0 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 455,637.5 91.6 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 460,579.6 92.3 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 432,036.4 93.0 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 435,199.7 93.5 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 430,529.2 94.1 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 371,445.5 94.5 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 345,643.3 94.7 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 271,112.6 94.3 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 223,943.8 93.6 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 304,905.9 93.2 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 292,323.1 93.0 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 423,503.2 93.1 1,840.0 0.0 0 0.00 0.000

0.0

09/06/09 456,536.0 93.4 1,840.0 0.0 0 0.00 0.000

0.2

09/06/09 500,733.7 93.9 1,840.0 0.0 0 0.00 0.000

09/06/09 527,362.6 94.5 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F FM

08:00 F F F F F F F F FM

09:00 F F F F F F F F FM

10:00 F F F F F F F F FM

11:00 F F F F F F F F FM

12:00 F F F F F F F F FM

13:00 F F F F F F F F FM

14:00 F F F F F F F F FM

15:00 F F F F F F F F FM

16:00 F F F F F F F F FM

17:00 F F F F F F F F FM

18:00 F F F F F F F F FM

19:00 F F F F F F F F FM

20:00 F F F F F F F F FM

21:00 F F F F F F F F FM

22:00 F F F F F F F F FM

23:00 F F F F F F F F FM

00:00 F F F F F F F F FM

01:00 F F F F F F F F FM

02:00 FC F F F F F F F FM

03:00 F F F F F F F F FM

04:00 F F F F F F F F FM

05:00 FC F F F F F F F FM

06:00 F F F F F F F F 0.0 FM

0.0

09/09/09 332,353.2 86.0 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 377,979.8 86.3 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 381,065.1 86.6 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 361,559.3 86.8 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 2,272,620.2 87.0 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 345,226.3 87.2 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 348,301.5 87.3 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 380,869.2 87.5 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 352,215.7 87.5 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 344,191.5 87.4 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 346,958.1 87.1 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 341,914.7 87.0 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 357,408.2 87.0 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 332,957.1 87.0 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 305,185.4 87.0 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 298,978.7 87.2 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 218,910.1 87.3 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 220,863.1 87.3 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 261,999.3 87.2 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 223,059.1 87.1 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 299,275.8 86.9 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 327,635.5 86.7 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 375,169.0 86.7 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 392,775.2 86.7 1,840.0 0.0 0 0.00 0.000

0.2

09/08/09 414,238.1 86.7 1,840.0 0.0 0 0.00 0.000

2.4

09/08/09 424,263.8 86.7 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 411,297.2 87.0 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 419,744.4 87.3 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 2,320,016.4 87.6 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 408,514.4 87.6 1,840.0 0.0 0 0.00 0.000

0.0

09/08/09 385,239.4 87.7 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 378,538.2 87.8 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 353,983.0 87.9 1,840.0 0.0 0 0.00 0.000

2.1

09/07/09 336,015.3 87.8 1,840.0 0.0 0 0.00 0.000

1.3

09/07/09 329,499.4 87.6 1,840.0 0.0 0 0.00 0.000

0.0

09/07/09 305,483.8 87.4 1,840.0 0.0 0 0.00 0.000

09/07/09 285,956.4 87.2 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

07:00 F F F F F F F F FM

08:00 F F F F F F F F FM

09:00 F F F F F F F F FM

10:00 F F F F F F F F FM

11:00 F F F F F F F F FM

12:00 F F F F F F F F FM

13:00 F F F F F F F F FM

14:00 F F F F F F F F FM

15:00 F F F F F F F F FM

16:00 F F F F F F F F FM

17:00 F F F F F F F F FM

18:00 F F F F F F F F FM

19:00 F F F F F F F F FM

20:00 F F F F F F F F FM

21:00 F F F F F F F F FM

22:00 F F F F F F F F FM

23:00 F F F F F F F F FM

00:00 F F F F F F F F FM

01:00 F F F F F F F F FM

02:00 FC F F F F F F F FM

03:00 F F F F F F F F FM

04:00 F F F F F F F F FM

05:00 FC F F F F F F F FM

06:00 F F F F F F F F FM

07:00 F F F F F F F F FM

08:00 F F F FIT F F FIT FI FIM

09:00 F F F F F F FI FI FIM

10:00 F F F F F F F F FM

11:00 F F F F F F F F FM

12:00 F F F F F F F F FM

13:00 F F F F F F F F FM

14:00 F F F F F F F F FM

15:00 F F F F F F F F FM

16:00 F F F F F F F F FM

17:00 F F F F F F F F FM

18:00 F F F F F F F F FM

19:00 F F F F F F F F 0.0 FM

0.0

09/10/09 575,354.1 92.6 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 572,740.5 92.3 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 578,911.2 92.0 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 581,220.4 91.7 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 598,504.8 91.3 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 602,447.7 90.6 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 614,769.2 89.6 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 646,646.4 87.9 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 683,678.6 86.7 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 689,399.5 86.9 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 683,842.5 87.2 1,840.0 0.0 0 0.00

0.0

09/10/09 670,266.4 87.4 1,840.0 0 0.00

0.0

09/10/09 685,196.7 87.4 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 697,687.6 87.4 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 692,228.3 87.5 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 708,836.8 87.7 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 727,601.7 87.9 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 2,507,877.6 87.9 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 698,261.1 87.9 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 704,792.2 88.2 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 713,210.7 88.3 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 725,379.4 88.5 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 694,113.9 88.7 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 627,586.7 89.1 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 601,869.1 89.5 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 610,059.2 89.8 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 616,732.9 89.9 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 585,216.2 90.1 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 585,303.1 90.6 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 609,860.2 90.8 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 603,849.8 91.0 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 610,769.7 91.0 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 611,552.0 90.8 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 593,771.7 90.5 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 647,924.1 90.0 1,840.0 0.0 0 0.00 0.000

0.0

09/09/09 375,902.6 86.5 1,840.0 0.0 0 0.00 0.000

09/09/09 306,149.0 85.9 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

20:00 F F F F F F F F FM

21:00 F F F F F F F F FM

22:00 F F F F F F F F FM

23:00 F F F F F F F F FM

00:00 F F F F F F F F FM

01:00 F F F F F F F F FM

02:00 FC F F F F F F F FM

03:00 F F F F F F F F FM

04:00 F F F F F F F F FM

05:00 FC F F F F F F F FM

06:00 F F F F F F F F FM

07:00 FIT F F FIT F F FIT FIT FIT

08:00 FC F F FI F F FIT FIT FIT

09:00 F F F F F F F F FM

10:00 F F F F F F F F FM

11:00 F F F F F F F F FM

12:00 F F F F F F F F FM

13:00 F F F F F F F F FM

14:00 F F F F F F F F FM

15:00 F F F F F F F F FM

16:00 F F F F F F F F FM

17:00 F F F F F F F F FM

18:00 F F F F F F F F FM

19:00 F F F F F F F F FM

20:00 F F F F F F F F FM

21:00 F F F F F F F F FM

22:00 F F F F F F F F FM

23:00 F F F F F F F F FM

00:00 F F F F F F F F FM

01:00 F F F F F F F F FM

02:00 FC F F F F F F F FM

03:00 F F F F F F F F FM

04:00 F F F F F F F F FM

05:00 FC F F F F F F F FM

06:00 F F F F F F F F FM

07:00 F F F F F F F F FM

08:00 F F F F F F F F 0.0 FM

0.0

09/12/09 678,420.6 83.7 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 751,317.2 83.3 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 756,273.6 83.1 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 747,550.7 83.5 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 740,050.2 83.9 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 722,948.5 84.5 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 2,512,906.2 85.3 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 728,336.2 85.8 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 722,588.8 86.4 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 725,527.5 87.0 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 729,324.7 87.5 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 704,457.7 87.9 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 678,504.6 88.3 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 662,786.6 88.9 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 662,481.1 89.4 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 681,930.2 89.7 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 646,687.8 90.1 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 639,480.2 90.6 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 650,588.2 91.1 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 635,744.1 91.4 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 645,461.3 91.6 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 626,812.1 91.6 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 618,971.9 91.5 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 608,380.2 91.6 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 626,378.6 91.7 1,840.0 0 0.00

0.0

09/11/09 1,307,564.2 91.7 1,840.0 0 0.00

0.0

09/11/09 604,365.0 92.2 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 631,744.1 93.1 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 663,960.1 94.0 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 674,414.5 94.5 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 2,476,007.3 94.6 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 671,729.9 94.9 1,840.0 0.0 0 0.00 0.000

0.0

09/11/09 677,310.7 94.9 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 673,100.4 94.7 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 662,775.3 94.4 1,840.0 0.0 0 0.00 0.000

0.0

09/10/09 639,693.8 94.0 1,840.0 0.0 0 0.00 0.000

09/10/09 605,227.7 93.4 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

09:00 F F F F F F F F FM

10:00 F F F F F F F F FM

11:00 F F F F F F F F FM

12:00 F F F F F F F F FM

13:00 F F F F F F F F FM

14:00 F F F F F F F F FM

15:00 F F F F F F F F FM

16:00 F F F F F F F F FM

17:00 F F F F F F F F FM

18:00 F F F F F F F F FM

19:00 F F F F F F F F FM

20:00 F F F F F F F F FM

21:00 F F F F F F F F FM

22:00 F F F F F F F F FM

23:00 F F F F F F F F FM

00:00 F F F F F F F F FM

01:00 F F F F F F F F FM

02:00 FC F F F F F F F FM

03:00 F F F F F F F F FM

04:00 F F F F F F F F FM

05:00 FC F F F F F F F FM

06:00 F F F F F F F F FM

07:00 F F F F F F F F FM

08:00 F F F F F F F F FM

09:00 F F F F F F F F FM

10:00 F F F F F F F F FM

11:00 F F F F F F F F FM

12:00 F F F F F F F F FM

13:00 F F F F F F F F FM

14:00 F F F F F F F F FM

15:00 F F F F F F F F FM

16:00 F F F F F F F F FM

17:00 F F F F F F F F FM

18:00 F F F F F F F F FM

19:00 F F F F F F F F FM

20:00 F F F F F F F F FM

21:00 F F F F F F F F 0.0 FM

0.0

09/13/09 786,122.9 83.3 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 788,787.4 83.7 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 744,498.7 84.0 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 730,342.2 84.2 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 738,680.0 84.5 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 735,751.5 85.0 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 743,513.3 85.3 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 730,178.1 85.6 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 710,483.6 85.6 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 699,426.6 85.1 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 698,104.2 84.2 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 721,384.3 83.0 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 761,637.1 81.5 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 773,234.7 80.5 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 767,748.5 80.0 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 740,487.4 79.9 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 715,380.7 80.1 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 713,736.1 80.3 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 730,102.6 80.5 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 2,511,633.2 81.0 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 711,187.2 81.5 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 709,436.8 82.2 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 718,186.7 82.8 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 727,660.9 83.5 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 733,335.8 84.1 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 698,229.3 84.5 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 677,517.8 84.8 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 688,997.7 85.2 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 676,969.2 85.3 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 655,967.3 85.5 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 650,813.8 85.7 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 645,301.8 85.9 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 652,470.8 85.9 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 623,921.4 85.6 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 621,663.8 85.1 1,840.0 0.0 0 0.00 0.000

0.0

09/12/09 632,755.8 84.6 1,840.0 0.0 0 0.00 0.000

09/12/09 635,803.6 84.0 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

22:00 F F F F F F F F FM

23:00 F F F F F F F F FM

00:00 F F F F F F F F FM

01:00 F F F F F F F F FM

02:00 FC F F F F F F F FM

03:00 F F F F F F F F FM

04:00 F F F F F F F F FM

05:00 FC F F F F F F F FM

06:00 F F F F F F F F FM

07:00 F F F F F F F F FM

08:00 F F F F F F F F FM

09:00 F F F F F F F F FM

10:00 F F F F F F F F FM

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F FMC

15:00 F F F F F F F F FC

16:00 F F F F F F F F FC

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F FM

01:00 F F F F F F F F FM

02:00 FC F F F F F F F FM

03:00 F F F F F F F F FM

04:00 F F F F F F F F FM

05:00 FC F F F F F F F FM

06:00 F F F F F F F F FM

07:00 F F F F F F F F FM

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F 0.0 F

0.0

09/15/09 2,842,361.3 87.4 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 2,519,524.9 86.3 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 677,768.3 84.5 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 708,278.2 84.4 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 735,273.3 84.2 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 701,094.1 84.1 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 762,904.9 83.7 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 789,112.4 83.3 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 2,563,598.1 83.5 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 797,987.7 83.8 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 799,832.4 84.2 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 789,578.4 84.6 1,840.0 0.0 0 0.00 0.000

3.1

09/14/09 787,856.2 85.0 1,840.0 0.0 0 0.00 0.000

0.3

09/14/09 748,175.5 85.3 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 715,369.4 85.6 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 688,544.5 85.8 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 684,662.3 86.1 1,840.0 0.0 0 0.00 0.000

2.7

09/14/09 702,542.4 86.3 1,840.0 0.0 0 0.00 0.000

1.9

09/14/09 700,861.6 86.4 1,840.0 0.0 0 0.00 0.000

0.8

09/14/09 697,438.9 86.4 1,840.0 0.0 0 0.00 0.000

0.6

09/14/09 680,174.5 86.3 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 685,757.0 86.1 1,840.0 0.0 0 0.00 0.000

0.1

09/14/09 686,031.8 85.7 1,840.0 0.0 0 0.00 0.000

0.7

09/14/09 691,082.0 85.2 1,840.0 0.0 0 0.00 0.000

0.2

09/14/09 695,299.8 84.3 1,840.0 0.0 0 0.00 0.000

0.1

09/14/09 696,390.1 83.3 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 711,366.1 82.8 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 753,281.0 82.5 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 753,701.4 82.3 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 741,932.6 82.4 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 737,801.7 82.5 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 755,456.7 82.7 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 2,538,211.2 82.9 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 768,638.0 83.0 1,840.0 0.0 0 0.00 0.000

0.0

09/14/09 775,487.7 83.2 1,840.0 0.0 0 0.00 0.000

0.0

09/13/09 780,580.9 83.2 1,840.0 0.0 0 0.00 0.000

09/13/09 791,773.0 83.2 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F* F F F* F F F F* F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F 0.0 F

0.0

09/16/09 3,536,980.1 80.2 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 3,486,535.3 79.6 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 3,200,919.6 79.6 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 3,073,263.1 80.1 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 3,012,851.5 80.3 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 2,733,661.8 80.6 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 2,752,176.9 80.6 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 2,718,810.5 80.5 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 2,676,188.5 80.5 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 2,686,822.4 80.6 1,840.0 8.8 0 0.00 0.000 0.000

0.0

09/16/09 2,672,299.0 80.7 1,840.0 66.8 0 0.00 0.000 0.000

0.0

09/16/09 3,109,511.0 80.6 1,840.0 37.2 0 0.00 0.000 0.000

0.0

09/16/09 2,648,393.7 80.2 1,840.0 56.1 0 0.00 0.000 0.000

0.0

09/16/09 2,647,652.9 79.4 1,840.0 57.6 0 0.00 0.000 0.000

0.0

09/16/09 2,897,010.5 79.2 1,840.0 64.6 0 0.00 0.000 0.000

0.0

09/16/09 2,970,607.2 79.2 1,840.0 30.7 0 0.00 0.000 0.000

0.0

09/16/09 3,003,192.7 79.7 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 3,188,630.9 80.2 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 3,235,824.9 80.8 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 3,526,246.3 81.6 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 3,456,334.1 82.1 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 4,422,641.3 83.0 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 3,625,505.5 83.2 1,840.0 0.0 0 0.00 0.000

0.0

09/16/09 3,630,375.4 83.4 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 3,585,862.9 83.8 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 3,577,263.8 84.1 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 3,400,175.7 85.1 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 3,050,232.6 85.4 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 2,987,912.1 85.5 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 2,959,440.6 85.4 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 2,926,147.8 85.7 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 2,807,169.3 86.1 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 2,781,569.5 87.1 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 2,836,465.1 87.0 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 2,791,777.4 86.8 1,840.0 0.0 0 0.00 0.000

0.0

09/15/09 2,764,474.3 87.1 1,840.0 0.0 0 0.00 0.000

09/15/09 2,851,786.0 87.3 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 FC F F F F F F F F

12:00 FC F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F 0.0 F

0.0

09/18/09 3,113,654.1 77.7 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,075,679.3 77.8 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,069,956.8 77.6 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,049,764.9 76.9 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,279,587.6 75.4 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,373,110.2 74.1 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,376,622.3 73.4 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,508,531.5 73.2 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,483,625.9 73.1 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,476,267.6 73.1 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 4,344,427.6 73.1 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,533,839.3 73.3 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,541,833.1 73.8 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 3,538,752.5 74.3 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 3,543,237.6 74.8 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 3,481,774.7 75.3 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 3,469,468.1 75.7 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 3,115,408.6 76.2 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 2,996,639.1 76.6 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 2,919,563.1 76.8 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 2,843,761.1 76.8 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 2,892,080.3 76.9 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 2,886,176.1 77.0 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 2,833,156.6 76.9 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 3,950,465.7 76.9 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 2,675,760.4 76.8 1,840.0 24.7 0 0.00 0.000 0.000

0.0

09/17/09 2,767,292.8 76.6 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 2,787,980.0 76.6 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 3,009,901.9 76.8 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 3,051,767.1 76.5 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 3,115,580.9 76.4 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 3,268,647.3 77.0 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 3,478,406.0 77.6 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 3,456,798.9 78.3 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 4,361,698.6 79.0 1,840.0 0.0 0 0.00 0.000

0.0

09/17/09 3,604,216.4 79.7 1,840.0 0.0 0 0.00 0.000

09/17/09 3,565,594.1 80.0 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F 0.0 F

0.0

09/20/09 3,558,463.6 75.3 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,502,983.6 76.1 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,530,156.7 75.8 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,534,446.2 75.5 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,524,909.3 75.4 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,482,976.0 75.5 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,300,063.0 75.5 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,146,267.1 75.7 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,385,143.8 75.8 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,182,262.4 76.1 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,175,043.7 76.4 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,080,336.0 76.6 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,261,733.2 76.7 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,365,780.5 76.8 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,461,400.6 76.7 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,426,448.7 76.6 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,356,149.1 76.5 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,221,128.1 76.2 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,432,417.8 76.0 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,485,426.9 76.6 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,556,861.8 77.2 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,590,389.0 77.9 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,545,130.0 78.6 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 4,385,849.9 78.9 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,523,561.9 78.9 1,840.0 0.0 0 0.00 0.000

0.0

09/19/09 3,551,614.9 78.7 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,592,685.3 78.9 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,600,456.5 78.7 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,486,576.9 78.5 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,277,911.6 78.5 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,201,414.9 78.5 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,127,607.4 78.3 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,156,453.9 78.2 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,170,287.3 77.8 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,140,810.1 77.6 1,840.0 0.0 0 0.00 0.000

0.0

09/18/09 3,178,823.0 77.8 1,840.0 0.0 0 0.00 0.000

09/18/09 3,144,309.1 77.7 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F 0.0 F

0.0

09/21/09 1,968,273.8 76.0 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 1,966,091.8 76.1 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,128,152.8 75.9 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,646,794.3 75.9 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,582,385.5 76.0 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,753,260.0 75.9 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,792,706.5 75.8 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,848,208.5 75.9 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 3,037,084.3 76.2 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 3,321,070.5 76.8 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 3,475,456.2 77.5 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 3,389,750.4 77.9 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 4,256,041.5 77.7 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 3,417,364.8 77.4 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 3,487,736.7 77.1 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,477,324.3 77.1 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,452,893.4 77.0 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,449,562.1 76.5 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,467,878.7 75.8 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,138,430.8 75.1 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,158,316.1 74.8 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,262,119.3 74.6 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,223,086.1 74.5 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,377,042.0 73.8 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,351,275.6 73.7 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,419,255.7 73.7 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,493,333.4 74.0 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,465,573.6 74.1 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,481,834.5 74.4 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,419,410.1 74.5 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,459,153.1 74.8 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,425,741.4 74.5 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,443,399.9 73.9 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,536,660.0 74.1 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,522,346.7 74.2 1,840.0 0.0 0 0.00 0.000

0.0

09/20/09 3,545,337.0 74.2 1,840.0 0.0 0 0.00 0.000

09/20/09 4,374,074.1 74.7 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F 0.0 F

0.0

09/23/09 3,409,315.4 78.0 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 4,312,619.8 78.2 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 3,426,400.0 78.3 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 3,432,373.5 78.5 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 3,422,996.0 78.9 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 3,226,766.9 79.3 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,955,786.9 79.3 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,868,699.1 79.2 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,787,497.2 79.0 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,849,685.4 78.7 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,752,743.9 78.5 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,796,157.5 78.0 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,694,304.5 77.8 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,768,393.2 77.6 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,732,145.0 77.3 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,631,931.2 76.9 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,680,309.6 76.6 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,669,183.6 76.4 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,704,514.7 76.2 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,587,290.7 75.8 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,119,823.3 75.2 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,097,840.2 74.5 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,110,921.9 74.2 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,237,796.9 74.2 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,365,778.0 74.5 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 3,662,175.2 74.7 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,483,166.3 75.1 1,840.0 0.0 0 0.00 0.000

0.0

09/22/09 2,408,438.5 75.4 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,436,770.0 75.6 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,402,799.0 75.7 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,238,169.9 75.7 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,185,675.3 75.7 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,030,572.9 75.9 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,022,312.6 76.1 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,074,682.0 76.3 1,840.0 0.0 0 0.00 0.000

0.0

09/21/09 2,041,861.0 76.4 1,840.0 0.0 0 0.00 0.000

09/21/09 1,983,462.5 76.3 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F 0.0 F

0.0

09/24/09 2,678,177.0 77.9 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,670,635.5 77.9 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,660,276.4 77.9 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,701,951.7 77.9 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,735,403.1 77.8 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,707,984.2 77.7 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,687,151.2 77.7 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,689,409.8 77.7 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,690,069.7 78.1 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,784,884.5 78.0 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,725,728.0 78.1 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,801,314.4 78.3 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 3,148,799.8 78.4 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 3,267,678.2 78.0 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 4,218,444.5 77.9 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 3,307,610.9 78.6 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 3,279,488.6 79.1 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 3,329,144.7 79.1 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 3,266,414.9 79.2 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 3,182,167.0 79.2 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 3,078,542.2 79.3 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,784,737.1 79.3 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,764,926.6 79.4 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,902,769.5 79.4 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,620,209.6 79.3 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,664,866.1 79.2 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,654,312.6 79.2 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,652,472.3 79.1 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,580,295.4 78.9 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,581,501.3 78.6 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,688,927.1 78.4 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,687,454.0 77.8 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,669,500.9 77.3 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,745,234.3 77.0 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 2,954,933.8 77.3 1,840.0 0.0 0 0.00 0.000

0.0

09/23/09 3,038,225.1 77.6 1,840.0 0.0 0 0.00 0.000

09/23/09 3,320,663.6 77.8 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F 0.0 F

0.0

09/26/09 3,122,770.1 76.8 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 3,254,320.6 77.3 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 3,291,751.0 77.8 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 4,269,517.2 78.1 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 3,401,700.3 78.2 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 3,317,158.1 78.3 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 3,360,611.7 78.3 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 3,398,041.1 78.1 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 3,081,547.8 78.1 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,771,721.0 78.1 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,723,377.6 78.2 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,674,785.4 77.9 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,623,783.7 77.6 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,714,009.8 77.4 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,750,077.6 77.3 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,767,841.0 77.4 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,773,594.8 77.2 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,785,092.5 77.0 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,800,182.8 76.9 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,881,403.0 77.0 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,850,421.5 76.8 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,826,537.5 77.3 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,816,100.1 77.6 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,831,283.5 77.8 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 2,922,747.7 77.9 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 3,261,006.4 78.0 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 3,339,299.3 78.1 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 4,249,412.4 78.1 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 3,359,099.1 78.3 1,840.0 0.0 0 0.00 0.000

0.0

09/25/09 3,336,664.5 78.4 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 3,266,383.6 78.2 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 3,282,175.4 78.0 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 3,047,548.4 77.9 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,931,786.3 77.9 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,690,254.5 77.9 1,840.0 0.0 0 0.00 0.000

0.0

09/24/09 2,651,015.6 77.9 1,840.0 0.0 0 0.00 0.000

09/24/09 2,641,228.6 77.9 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F 0.0 F

0.0

09/27/09 2,855,395.1 74.7 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 2,712,931.4 75.0 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,059,157.4 74.9 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 2,968,202.5 74.1 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,157,191.4 73.8 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,172,534.9 73.3 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,152,365.1 73.2 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,272,708.4 72.9 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,249,389.7 72.6 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,306,683.8 72.5 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,307,124.5 72.4 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,308,208.4 72.3 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,370,796.0 72.6 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,310,861.0 72.9 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,349,156.7 73.4 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,382,301.9 73.9 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 4,268,899.2 74.4 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,345,300.9 74.8 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,342,951.1 75.3 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 3,351,962.1 75.6 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 3,362,198.6 76.0 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 3,352,943.1 76.2 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 3,046,628.0 76.3 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 2,588,660.0 76.3 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 2,516,028.7 76.3 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 2,494,121.8 75.8 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 2,585,950.8 75.4 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 2,659,513.3 75.4 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 2,621,062.0 75.4 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 2,632,201.0 75.4 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 2,643,197.6 75.5 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 2,671,223.9 75.5 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 2,730,910.3 75.7 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 2,695,658.9 75.9 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 2,821,472.6 76.0 1,840.0 0.0 0 0.00 0.000

0.0

09/26/09 2,928,886.2 76.2 1,840.0 0.0 0 0.00 0.000

09/26/09 3,012,095.5 76.4 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F 0.0 F

0.0

09/29/09 3,252,118.1 70.3 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,321,435.8 70.1 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,198,442.4 69.9 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,437,502.4 70.0 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,572,782.6 70.0 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 4,416,934.5 70.1 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,570,505.7 70.2 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,519,875.4 70.5 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,507,208.4 70.8 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,500,542.0 71.0 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,529,665.6 71.2 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,447,380.3 71.4 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,265,375.2 71.5 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 2,969,162.8 71.5 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,077,791.4 71.7 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,196,103.2 72.1 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,123,054.2 72.6 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,111,438.5 72.7 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,084,809.3 72.6 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 2,824,221.3 72.1 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 2,885,265.5 71.9 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,145,053.5 71.9 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,033,269.9 71.9 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 2,902,776.0 71.9 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,030,370.8 72.3 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,050,188.6 72.6 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,242,888.5 72.9 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,437,774.6 73.1 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,394,554.5 73.0 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 4,267,164.5 72.8 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,433,416.6 72.8 1,840.0 0.0 0 0.00 0.000

0.0

09/28/09 3,411,017.1 72.8 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,347,474.1 73.1 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,367,851.9 73.0 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,336,723.3 73.4 1,840.0 0.0 0 0.00 0.000

0.0

09/27/09 3,137,811.2 74.6 1,840.0 0.0 0 0.00 0.000

09/27/09 3,055,349.1 74.5 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 FIM FIM F FI FI F FI FI F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F 0.0 F

0.0

09/30/09 3,242,613.0 75.0 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,026,688.2 75.0 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,014,508.9 74.8 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,183,091.6 74.7 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,190,214.4 74.5 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 2,978,000.1 74.1 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,061,575.0 74.0 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,076,768.3 73.7 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,125,739.7 73.4 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,174,630.8 73.2 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,107,682.2 72.9 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,136,100.1 72.6 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,195,699.2 72.6 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,246,383.4 72.6 1,840.0 0 0.00

0.0

09/30/09 3,354,237.3 72.8 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,334,050.9 73.3 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,469,544.4 74.0 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,630,852.8 74.6 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 4,471,550.3 75.3 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,695,976.0 75.7 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,710,566.5 76.1 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,667,944.0 76.3 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,671,587.0 76.5 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,602,314.7 76.4 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,352,389.3 76.2 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,175,190.7 75.9 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,129,916.4 75.7 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,065,867.5 75.3 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,148,319.6 74.9 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,131,421.5 74.4 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,117,001.2 73.9 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,071,221.2 73.3 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,056,662.3 72.8 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,100,365.9 72.2 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,125,792.5 71.6 1,840.0 0.0 0 0.00 0.000

0.0

09/29/09 3,143,952.0 71.0 1,840.0 0.0 0 0.00 0.000

09/29/09 3,183,274.7 70.6 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 FIT FI F FIT FI F FIT FIT F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 FIT F F FIT F F FIT FIT FIT

08:00 F F F FI F F FIT FIT FIT

09:00 F F F FI F F FIT FIT 0.0 FIT

0.0

10/02/09 2,848,376.1 72.0 1,840.0 0 0.00

0.0

10/02/09 2,907,851.4 72.1 1,840.0 0 0.00

0.0

10/02/09 3,936,357.5 72.2 1,840.0 0 0.00

0.0

10/02/09 2,932,874.8 72.4 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 3,153,562.4 72.7 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 3,471,791.2 73.1 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 3,547,438.7 73.3 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 4,331,249.4 73.7 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 3,427,299.8 74.0 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 3,450,770.9 74.2 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,430,478.0 74.7 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,488,601.1 75.2 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,442,118.4 75.5 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,381,820.5 75.2 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,158,552.9 75.0 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,102,712.5 75.0 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,080,652.5 75.3 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,189,514.9 75.5 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,158,822.0 75.6 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,054,047.3 75.7 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,048,696.9 75.8 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,093,460.7 75.7 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,070,650.1 75.5 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,120,082.6 75.3 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,231,537.4 74.9 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,353,569.4 74.6 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,127,092.9 74.7 1,840.0 0 0.00

0.0

10/01/09 3,276,178.5 74.8 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,558,493.3 75.3 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,611,593.6 75.6 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,557,705.9 75.7 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 4,415,369.8 76.0 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,543,686.9 76.1 1,840.0 0.0 0 0.00 0.000

0.0

10/01/09 3,621,227.4 75.9 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,511,409.7 75.7 1,840.0 0.0 0 0.00 0.000

0.0

09/30/09 3,457,873.1 75.6 1,840.0 0.0 0 0.00 0.000

09/30/09 3,477,115.1 75.3 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F 0.0 F

0.0

10/03/09 3,481,799.6 74.0 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,365,227.5 73.9 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,225,079.3 73.8 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,037,865.2 73.7 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,159,152.1 73.6 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,319,451.9 73.5 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,352,520.6 73.4 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,242,465.0 73.1 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,352,413.1 72.9 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,352,121.3 72.6 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,345,631.7 72.5 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,286,930.7 72.5 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,274,258.9 72.6 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,337,135.7 72.8 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,195,180.1 73.1 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,179,520.0 73.4 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,407,703.1 73.9 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,367,638.2 74.2 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,468,802.4 74.5 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,492,558.4 74.9 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 4,330,805.9 75.2 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,459,850.8 75.4 1,840.0 0.0 0 0.00 0.000

0.0

10/03/09 3,414,159.2 75.5 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 3,432,547.2 75.6 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 3,422,707.2 75.5 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 3,190,667.4 75.3 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 3,205,613.4 75.2 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 3,094,993.1 75.2 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 3,031,578.4 75.0 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 3,011,677.0 74.8 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 2,957,420.0 74.6 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 2,950,253.5 74.2 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 2,882,164.2 73.6 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 2,884,526.7 73.2 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 2,879,652.6 72.7 1,840.0 0.0 0 0.00 0.000

0.0

10/02/09 2,930,334.2 72.1 1,840.0 0.0 0 0.00 0.000

10/02/09 2,897,724.0 71.8 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F 0.0 F

0.0

10/05/09 2,947,987.5 71.8 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 2,938,634.1 71.4 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 3,003,819.5 71.1 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 2,986,487.5 71.0 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 2,988,887.7 71.0 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 3,096,107.4 71.2 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 3,052,013.1 71.5 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 3,271,929.0 71.9 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 3,490,674.0 72.4 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 4,369,886.3 73.2 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 3,529,764.8 73.7 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 3,506,676.7 74.5 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,544,603.3 75.1 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,508,997.0 75.5 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,475,710.1 75.5 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,317,416.9 75.3 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,112,189.9 75.1 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,134,056.0 75.0 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,247,257.9 74.8 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,212,781.2 74.6 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,275,347.0 74.4 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,319,700.0 74.2 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,317,173.9 74.0 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,389,571.5 73.7 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,347,305.4 73.7 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,308,417.1 73.6 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,387,287.7 73.6 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,338,368.6 73.6 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,195,684.8 73.6 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,408,939.0 73.7 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,435,937.1 73.6 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,497,221.5 73.7 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,523,293.8 73.6 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 4,368,833.5 73.8 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,533,435.3 73.8 1,840.0 0.0 0 0.00 0.000

0.0

10/04/09 3,545,982.2 73.9 1,840.0 0.0 0 0.00 0.000

10/03/09 3,518,609.1 73.9 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F 0.0 F

0.0

10/07/09 3,452,863.9 70.3 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,421,055.8 70.7 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,515,721.8 71.4 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,436,074.0 71.9 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,259,927.9 72.4 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 2,848,119.7 72.3 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 2,849,735.9 72.4 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,194,719.6 72.3 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,135,978.3 72.3 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,044,500.5 72.6 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 2,997,085.0 73.0 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 2,985,916.3 73.0 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 2,937,207.7 73.0 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 2,927,910.5 73.0 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 2,953,837.5 73.2 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 2,996,752.7 73.3 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,037,230.4 73.4 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,053,319.7 73.7 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,015,426.2 74.1 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,283,877.8 74.4 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,486,508.5 74.7 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,516,761.5 74.8 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 4,376,494.9 74.8 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,461,519.5 74.8 1,840.0 0.0 0 0.00 0.000

0.0

10/06/09 3,463,620.8 74.8 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 3,525,224.1 74.8 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 3,532,957.3 74.9 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 3,408,350.9 75.0 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 3,098,276.9 74.8 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 3,099,019.9 74.7 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 2,993,636.5 74.5 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 2,988,028.6 74.5 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 3,006,320.6 74.4 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 2,983,388.8 74.2 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 2,990,923.9 73.7 1,840.0 0.0 0 0.00 0.000

0.0

10/05/09 2,965,332.4 72.9 1,840.0 0.0 0 0.00 0.000

10/05/09 2,946,209.6 72.3 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F 0.0 F

0.0

10/08/09 2,530,029.3 75.2 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 2,573,648.8 75.1 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 2,594,222.6 74.8 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 2,634,588.9 74.7 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 2,660,307.1 74.6 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 2,632,703.2 74.5 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 2,766,116.1 74.6 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 2,961,322.0 74.8 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 3,106,101.9 74.9 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 3,181,391.8 75.1 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 3,166,638.2 75.1 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 4,135,893.0 75.1 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 3,195,206.6 75.0 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 3,274,194.2 75.0 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,378,004.4 75.0 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,240,175.7 74.8 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,104,076.1 74.8 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,098,996.2 74.7 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 2,987,280.0 74.6 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,058,860.1 74.4 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,111,805.0 74.0 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,191,568.0 73.5 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,272,095.2 73.0 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,333,187.1 72.3 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,319,120.1 71.7 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,135,936.6 71.0 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,022,720.8 70.5 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,012,878.4 70.1 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 2,983,578.6 69.8 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,030,050.9 69.5 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,074,096.6 69.1 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,160,915.5 68.8 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,418,691.4 68.8 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,478,364.9 68.9 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 3,474,077.8 69.0 1,840.0 0.0 0 0.00 0.000

0.0

10/07/09 4,317,094.3 69.3 1,840.0 0.0 0 0.00 0.000

10/07/09 3,417,447.3 69.7 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F FIT FIT FIT

12:00 F F F F F F FIT FIT FIT

13:00 F F F F F F FIT FIT FIT

14:00 F F F F F F FIT FIT FIT

15:00 F F F F F F FIT FIT FIT

16:00 F F F F F F FIT FIT FIT

17:00 F F F F F F FIT FIT FIT

18:00 F F F F F F FIT FIT FIT

19:00 F F F F F F FIT FIT FIT

20:00 F F F F F F FIT FIT FIT

21:00 F F F F F F FIT FIT FIT

22:00 F F F F F F FIT FIT FIT

23:00 F F F F F F FIT FIT FIT

00:00 F F F F F F FIT FIT FIT

01:00 F F F F F F FIT FIT FIT

02:00 FC F F F F F FIT FIT 0.0 FIT

0.0

10/10/09 4,213,540.1 72.5 1,840.0 0.0 0 0.00

0.0

10/10/09 3,298,738.3 73.1 1,840.0 0.0 0 0.00

0.0

10/10/09 3,255,853.7 73.5 1,840.0 0.0 0 0.00

0.0

10/09/09 3,242,697.2 73.8 1,840.0 0.0 0 0.00

0.0

10/09/09 3,225,060.8 74.1 1,840.0 0.0 0 0.00

0.0

10/09/09 3,075,432.2 74.3 1,840.0 0.0 0 0.00

0.0

10/09/09 2,825,829.8 74.5 1,840.0 0.0 0 0.00

0.0

10/09/09 2,684,157.1 74.4 1,840.0 0.0 0 0.00

0.0

10/09/09 2,694,280.1 74.4 1,840.0 0.0 0 0.00

0.0

10/09/09 2,677,408.7 74.4 1,840.0 0.0 0 0.00

0.0

10/09/09 2,714,191.4 74.4 1,840.0 0.0 0 0.00

0.0

10/09/09 2,890,715.6 74.4 1,840.0 0.0 0 0.00

0.0

10/09/09 2,833,086.7 74.2 1,840.0 0.0 0 0.00

0.0

10/09/09 2,825,536.0 74.1 1,840.0 0.0 0 0.00

0.0

10/09/09 2,797,576.0 74.1 1,840.0 0.0 0 0.00

0.0

10/09/09 2,794,282.8 74.1 1,840.0 0.0 0 0.00

0.0

10/09/09 2,800,379.9 74.1 1,840.0 0.0 0 0.00 0.000

0.0

10/09/09 2,846,936.8 74.1 1,840.0 0.0 0 0.00 0.000

0.0

10/09/09 2,839,867.5 74.3 1,840.0 0.0 0 0.00 0.000

0.0

10/09/09 2,842,915.7 74.6 1,840.0 0.0 0 0.00 0.000

0.0

10/09/09 2,868,053.1 74.7 1,840.0 0.0 0 0.00 0.000

0.0

10/09/09 2,986,596.5 74.9 1,840.0 0.0 0 0.00 0.000

0.0

10/09/09 3,170,995.0 75.2 1,840.0 0.0 0 0.00 0.000

0.0

10/09/09 3,164,694.6 75.6 1,840.0 0.0 0 0.00 0.000

0.0

10/09/09 4,178,794.7 75.9 1,840.0 0.0 0 0.00 0.000

0.0

10/09/09 3,208,025.1 75.9 1,840.0 0.0 0 0.00 0.000

0.0

10/09/09 3,225,671.7 76.0 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 3,187,389.3 76.1 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 3,225,285.6 76.1 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 3,103,139.3 76.1 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 2,876,282.3 75.9 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 2,658,495.6 75.7 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 2,635,010.5 75.6 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 2,549,977.3 75.6 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 2,571,530.2 75.5 1,840.0 0.0 0 0.00 0.000

0.0

10/08/09 2,549,613.3 75.4 1,840.0 0.0 0 0.00 0.000

10/08/09 2,556,319.2 75.3 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

03:00 F F F F F F FIT FIT FIT

04:00 F F F F F F FIT FIT FIT

05:00 FC F F F F F FIT FIT FIT

06:00 F F F F F F FIT FIT FIT

07:00 F F F F F F FIT FIT FIT

08:00 F F F F F F FIT FIT FIT

09:00 F F F F F F FIT FIT FIT

10:00 F F F F F F FIT FIT FIT

11:00 F F F F F F FIT FIT FIT

12:00 F F F F F F FIT FIT FIT

13:00 F F F F F F FIT FIT FIT

14:00 F F F F F F FIT FIT FIT

15:00 F F F F F F FIT FIT FIT

16:00 F F F F F F FIT FIT FIT

17:00 F F F F F F FIT FIT FIT

18:00 F F F F F F FIT FIT FIT

19:00 F F F F F F FIT FIT FIT

20:00 F F F F F F FIT FIT FIT

21:00 F F F F F F FIT FIT FIT

22:00 F F F F F F FIT FIT FIT

23:00 F F F F F F FIT FIT FIT

00:00 F F F F F F FIT FIT FIT

01:00 F F F F F F FIT FIT FIT

02:00 FC F F F F F FIT FIT FIT

03:00 F F F F F F FIT FIT FIT

04:00 F F F F F F FIT FIT FIT

05:00 FC F F F F F FIT FIT FIT

06:00 F F F F F F FIT FIT FIT

07:00 F F F F F F FIT FIT FIT

08:00 F F F F F F FIT FIT FIT

09:00 F F F F F F FIT FIT FIT

10:00 F F F F F F FIT FIT FIT

11:00 F F F F F F FIT FIT FIT

12:00 F F F F F F FIT FIT FIT

13:00 F F F F F F FIT FIT FIT

14:00 F F F F F F FIT FIT FIT

15:00 F F F F F F FIT FIT 0.0 FIT

0.0

10/11/09 3,002,207.4 67.9 1,840.0 0.0 0 0.00

0.0

10/11/09 3,133,510.6 67.5 1,840.0 0.0 0 0.00

0.0

10/11/09 3,148,567.3 67.0 1,840.0 0.0 0 0.00

0.0

10/11/09 3,231,835.8 66.6 1,840.0 0.0 0 0.00

0.0

10/11/09 2,962,148.6 66.1 1,840.0 0.0 0 0.00

0.0

10/11/09 3,028,292.5 65.9 1,840.0 0.0 0 0.00

0.0

10/11/09 3,033,003.8 65.5 1,840.0 0.0 0 0.00

0.0

10/11/09 3,043,059.1 65.2 1,840.0 0.0 0 0.00

0.0

10/11/09 3,125,499.4 65.0 1,840.0 0.0 0 0.00

0.0

10/11/09 3,227,521.6 65.2 1,840.0 0.0 0 0.00

0.0

10/11/09 3,323,120.5 65.7 1,840.0 0.0 0 0.00

0.0

10/11/09 3,410,605.5 66.2 1,840.0 0.0 0 0.00

0.0

10/11/09 3,391,090.5 66.7 1,840.0 0.0 0 0.00

0.0

10/11/09 4,307,830.3 67.1 1,840.0 0.0 0 0.00

0.0

10/11/09 3,402,381.4 67.5 1,840.0 0.0 0 0.00

0.0

10/11/09 3,365,429.2 67.8 1,840.0 0.0 0 0.00

0.0

10/10/09 3,355,616.0 68.0 1,840.0 0.0 0 0.00

0.0

10/10/09 3,292,537.8 68.2 1,840.0 0.0 0 0.00

0.0

10/10/09 3,137,492.0 68.3 1,840.0 0.0 0 0.00

0.0

10/10/09 3,085,920.8 68.4 1,840.0 0.0 0 0.00

0.0

10/10/09 2,958,471.0 68.6 1,840.0 0.0 0 0.00

0.0

10/10/09 3,064,477.0 68.7 1,840.0 0.0 0 0.00

0.0

10/10/09 3,068,551.2 68.7 1,840.0 0.0 0 0.00

0.0

10/10/09 3,199,802.7 68.8 1,840.0 0.0 0 0.00

0.0

10/10/09 3,220,025.2 68.9 1,840.0 0.0 0 0.00

0.0

10/10/09 3,320,342.8 68.9 1,840.0 0.0 0 0.00

0.0

10/10/09 3,274,979.2 69.2 1,840.0 0.0 0 0.00

0.0

10/10/09 3,273,841.3 69.8 1,840.0 0.0 0 0.00

0.0

10/10/09 3,265,387.3 70.2 1,840.0 0.0 0 0.00

0.0

10/10/09 3,082,524.9 70.1 1,840.0 0.0 0 0.00

0.0

10/10/09 3,180,762.5 70.0 1,840.0 0.0 0 0.00

0.0

10/10/09 3,021,432.0 69.8 1,840.0 0.0 0 0.00

0.0

10/10/09 3,064,368.1 69.8 1,840.0 0.0 0 0.00

0.0

10/10/09 3,157,845.6 70.2 1,840.0 0.0 0 0.00

0.0

10/10/09 3,218,557.4 70.8 1,840.0 0.0 0 0.00

0.0

10/10/09 3,263,278.4 71.4 1,840.0 0.0 0 0.00

10/10/09 3,307,268.3 72.1 1,840.0 0.0 0 0.00
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

16:00 F F F F F F FIT FIT FIT

17:00 F F F F F F FIT FIT FIT

18:00 F F F F F F FIT FIT FIT

19:00 F F F F F F FIT FIT FIT

20:00 F F F F F F FIT FIT FIT

21:00 F F F F F F FIT FIT FIT

22:00 F F F F F F FIT FIT FIT

23:00 F F F F F F FIT FIT FIT

00:00 F F F F F F FIT FIT FIT

01:00 F F F F F F FIT FIT FIT

02:00 FC F F F F F FIT FIT FIT

03:00 F F F F F F FIT FIT FIT

04:00 F F F F F F FIT FIT FIT

05:00 FC F F F F F FIT FIT FIT

06:00 F F F F F F FIT FIT FIT

07:00 F F F F F F FIT FIT FIT

08:00 F F F F F F FIT FIT FIT

09:00 F F F F F F FIT FIT FIT

10:00 F F F F F F FIT FIT FIT

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F 2.4 FC

0.0

10/13/09 2,084,209.9 65.4 1,840.0 0.0 0 0.00 0.000

0.0

10/13/09 2,057,962.5 65.6 1,840.0 0.0 0 0.00 0.000

0.0

10/13/09 3,358,611.6 66.0 1,840.0 0.0 0 0.00 0.000

0.0

10/13/09 1,974,154.0 66.2 1,840.0 0.0 0 0.00 0.000

0.0

10/13/09 2,045,134.8 66.5 1,840.0 0.0 0 0.00 0.000

0.0

10/12/09 1,971,384.5 66.7 1,840.0 0.0 0 0.00 0.000

0.0

10/12/09 1,978,621.7 67.0 1,840.0 0.0 0 0.00 0.000

0.0

10/12/09 1,917,738.7 67.1 1,840.0 0.0 0 0.00 0.000

0.0

10/12/09 1,934,731.7 67.4 1,840.0 0.0 0 0.00 0.000

0.0

10/12/09 1,877,846.0 67.6 1,840.0 0.0 0 0.00 0.000

0.0

10/12/09 1,934,737.6 67.9 1,840.0 0.0 0 0.00 0.000

0.0

10/12/09 1,907,574.6 68.2 1,840.0 0.0 0 0.00 0.000

0.0

10/12/09 1,840,277.1 68.2 1,840.0 0.0 0 0.00 0.000

0.0

10/12/09 1,785,426.7 68.1 1,840.0 0.0 0 0.00 0.000

0.0

10/12/09 1,845,387.7 68.1 1,840.0 0.0 0 0.00 0.000

0.0

10/12/09 1,892,282.5 68.2 1,840.0 0.0 0 0.00 0.000

0.0

10/12/09 1,921,292.9 68.3 1,840.0 0.0 0 0.00 0.000

2.7

10/12/09 1,917,771.7 68.4 1,840.0 31.3 0 0.00 0.000 0.000

0.0

10/12/09 1,921,146.3 68.3 1,840.0 0.0 0 0.00

0.0

10/12/09 1,923,632.6 68.3 1,840.0 0.0 0 0.00

0.0

10/12/09 1,899,421.7 68.4 1,840.0 0.0 0 0.00

0.0

10/12/09 2,433,016.1 68.9 1,840.0 0.0 0 0.00

0.0

10/12/09 2,745,561.7 68.9 1,840.0 0.0 0 0.00

0.0

10/12/09 2,813,586.2 69.0 1,840.0 0.0 0 0.00

0.0

10/12/09 2,956,333.1 69.1 1,840.0 0.0 0 0.00

0.0

10/12/09 3,086,180.0 69.3 1,840.0 0.0 0 0.00

0.0

10/12/09 4,159,740.4 69.3 1,840.0 0.0 0 0.00

0.0

10/12/09 3,245,395.2 69.1 1,840.0 0.0 0 0.00

0.0

10/12/09 3,240,122.2 68.8 1,840.0 0.0 0 0.00

0.0

10/11/09 3,224,890.3 68.4 1,840.0 0.0 0 0.00

0.0

10/11/09 3,130,386.0 68.0 1,840.0 0.0 0 0.00

0.0

10/11/09 2,807,496.4 67.8 1,840.0 0.0 0 0.00

0.0

10/11/09 2,831,540.0 67.9 1,840.0 0.0 0 0.00

0.0

10/11/09 2,771,318.6 68.1 1,840.0 0.0 0 0.00

0.0

10/11/09 2,802,986.2 68.3 1,840.0 0.0 0 0.00

0.0

10/11/09 2,848,080.2 68.4 1,840.0 0.0 0 0.00

10/11/09 3,011,864.9 68.2 1,840.0 0.0 0 0.00
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00

16:00

17:00

18:00 C

19:00 S S SC

20:00

21:00 C

22:00

23:00

00:00

01:00 C

02:00 C S S SC

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00 0.4

0.6

10/14/09 9,874,338.9 277.0 1,840.0 563.5 50 60.00 0.461 0.004

0.7

10/14/09 9,934,021.2 279.0 1,840.0 561.5 50 60.00 0.641 0.006

0.7

10/14/09 9,931,389.4 279.2 1,840.0 561.3 50 60.00 0.805 0.007

0.5

10/14/09 9,905,281.7 278.6 1,840.0 549.1 50 60.00 0.759 0.007

0.4

10/14/09 9,921,833.4 277.4 1,840.0 528.5 50 60.00 0.608 0.005

0.4

10/14/09 9,883,344.3 275.2 1,840.0 590.8 50 60.00 0.452 0.004

0.4

10/14/09 9,880,907.2 272.1 1,840.0 590.7 50 60.00 0.465 0.004

0.5

10/14/09 9,910,347.8 266.8 1,840.0 603.2 50 60.00 0.376 0.004

0.7

10/14/09 9,871,039.1 258.0 1,840.0 536.5 50 60.00 0.521 0.004

0.7

10/14/09 9,702,173.8 233.4 1,840.0 601.1 49 60.00 0.686 0.007

0.7

10/14/09 5,480,187.3 208.5 1,840.0 309.7 26 60.00 0.740 0.004

0.9

10/14/09 4,824,576.8 204.9 1,840.0 267.5 23 60.00 0.811 0.003

1.2

10/14/09 4,867,285.3 202.2 1,840.0 267.2 23 60.00 1.021 0.004

1.3

10/14/09 4,919,999.2 198.7 1,840.0 270.1 23 60.00 1.338 0.006

1.3

10/14/09 4,975,510.9 191.8 1,840.0 270.4 23 60.00 1.432 0.006

1.3

10/14/09 5,024,130.2 180.8 1,840.0 267.6 21 60.00 1.460 0.006

1.1

10/14/09 4,153,057.8 173.5 1,840.0 191.9 13 60.00 1.795 0.005

0.5

10/14/09 3,781,206.8 170.6 1,840.0 121.2 5 60.00 2.097 0.004

0.4

10/13/09 3,550,550.4 167.5 1,840.0 73.3 1 60.00 1.611 0.002

0.2

10/13/09 3,484,158.9 161.1 1,840.0 53.0 0 60.00 1.570 0.001

0.1

10/13/09 3,561,001.8 151.0 1,840.0 52.3 0 60.00 0.942 0.001

0.1

10/13/09 3,442,376.3 139.0 1,840.0 29.9 0 60.00 0.564 0.000

0.2

10/13/09 3,529,857.6 124.7 1,840.0 32.6 0 60.00 0.978 0.000

0.5

10/13/09 3,760,142.0 118.3 1,840.0 92.0 0 60.00 0.523 0.001

0.6

10/13/09 3,932,801.2 110.6 1,840.0 102.6 0 60.00 1.185 0.002

0.0

10/13/09 3,688,814.7 90.2 1,840.0 54.1 0 60.00 2.577 0.002

0.0

10/13/09 1,823,867.0 75.6 1,840.0 1.0 0 2.00 0.000

0.0

10/13/09 740,251.4 64.9 1,840.0 0.0 0 0.00 0.000

0.5

10/13/09 522,818.9 48.5 1,840.0 0.0 0 0.00 0.000

4.5

10/13/09 0.0 4.8 1,840.0 0.0 0 0.00 0.000

1.4

10/13/09 721,200.3 62.3 1,840.0 0.0 0 0.00 0.000

0.0

10/13/09 1,389,469.4 66.4 1,840.0 0.0 0 0.00 0.000

0.0

10/13/09 2,003,593.2 66.2 1,840.0 0.0 0 0.00 0.000

0.0

10/13/09 2,020,857.1 65.4 1,840.0 0.0 0 0.00 0.000

0.0

10/13/09 2,028,573.3 64.9 1,840.0 0.0 0 0.00 0.000

0.2

10/13/09 2,024,002.8 64.8 1,840.0 0.0 0 0.00 0.000

10/13/09 2,019,744.8 65.1 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C ST ST

03:00 ST ST

04:00 ST ST C

05:00 C ST ST C

06:00 ST ST

07:00 C

08:00 C

09:00 C

10:00 C

11:00 C

12:00 C

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00 0.1

0.0

10/16/09 6,176,079.9 231.9 1,840.0 312.2 26 60.00 0.105 0.001

0.0

10/16/09 5,567,007.8 232.4 1,840.0 269.3 22 60.00 0.052 0.000

0.1

10/16/09 5,572,700.2 234.5 1,840.0 269.6 22 60.00 0.013 0.000

0.1

10/16/09 5,565,769.2 239.4 1,840.0 263.2 22 60.00 0.135 0.001

0.2

10/16/09 5,564,043.4 247.1 1,840.0 257.0 22 60.00 0.139 0.001

0.1

10/16/09 5,585,943.4 257.8 1,840.0 267.2 23 60.00 0.255 0.001

0.2

10/16/09 8,397,749.2 268.2 1,840.0 442.7 39 60.00 0.167 0.001

0.2

10/15/09 8,473,461.3 274.5 1,840.0 446.7 40 60.00 0.187 0.001

0.2

10/15/09 9,932,252.8 285.6 1,840.0 561.4 51 60.00 0.272 0.002

0.1

10/15/09 11,132,460.2 287.3 1,840.0 659.5 60 60.00 0.255 0.003

0.2

10/15/09 11,154,218.9 289.0 1,840.0 654.7 60 60.00 0.152 0.002

0.3

10/15/09 11,152,360.6 288.9 1,840.0 660.6 60 60.00 0.203 0.002

0.2

10/15/09 11,160,459.1 288.0 1,840.0 655.0 60 60.00 0.269 0.003

0.2

10/15/09 11,153,303.9 290.1 1,840.0 654.6 60 60.00 0.175 0.002

0.2

10/15/09 11,181,239.8 290.5 1,840.0 656.3 60 60.00 0.259 0.003

0.2

10/15/09 11,109,283.1 289.2 1,840.0 652.1 60 60.00 0.219 0.002

0.2

10/15/09 11,123,185.4 288.8 1,840.0 652.9 60 60.00 0.229 0.002

0.4

10/15/09 11,065,397.2 295.4 1,840.0 643.5 60 60.00 0.259 0.003

0.7

10/15/09 13,140,848.3 313.7 1,840.0 778.5 72 60.00 0.409 0.005

0.7

10/15/09 14,090,444.0 315.7 1,840.0 842.3 76 60.00 0.735 0.010

0.5

10/15/09 14,024,502.0 312.8 1,840.0 838.5 76 60.00 0.755 0.010

0.3

10/15/09 14,019,687.7 305.9 1,840.0 838.2 76 60.00 0.563 0.008

0.0

10/15/09 13,974,104.5 287.1 1,840.0 827.8 76 60.00 0.300 0.004

0.0

10/15/09 8,478,842.7 241.3 1,840.0 479.2 41 60.00 0.000 0.000

0.0

10/15/09 5,688,522.8 233.1 1,840.0 303.0 24 60.00 0.035 0.000

0.0

10/15/09 5,603,373.8 235.0 1,840.0 298.4 24 60.00 0.008 0.000

0.0

10/15/09 5,638,177.5 236.2 1,840.0 300.3 24 60.00 0.000 0.000

0.0

10/15/09 5,643,753.6 238.8 1,840.0 300.6 24 60.00 0.000 0.000

0.0

10/15/09 5,652,506.8 243.4 1,840.0 301.1 24 60.00 0.000 0.000

0.2

10/15/09 5,726,536.3 249.9 1,840.0 286.4 24 60.00 0.000 0.000

0.1

10/15/09 6,637,929.3 260.4 1,840.0 339.1 30 60.00 0.192 0.001

0.5

10/14/09 7,971,010.4 268.0 1,840.0 424.5 38 60.00 0.166 0.001

0.4

10/14/09 8,424,056.8 276.9 1,840.0 457.8 40 60.00 0.566 0.004

0.3

10/14/09 9,938,880.6 282.5 1,840.0 572.6 50 60.00 0.422 0.004

0.3

10/14/09 10,024,528.3 282.2 1,840.0 577.5 51 60.00 0.358 0.003

0.2

10/14/09 10,034,492.1 281.1 1,840.0 578.0 51 60.00 0.366 0.003

10/14/09 10,012,882.4 278.7 1,840.0 576.8 51 60.00 0.263 0.002
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00 1.0

1.1

10/17/09 10,284,669.2 286.7 1,840.0 620.5 55 60.00 1.088 0.011

1.2

10/17/09 10,270,548.6 286.8 1,840.0 614.0 55 60.00 1.187 0.012

1.1

10/17/09 10,287,410.8 285.9 1,840.0 615.0 55 60.00 1.203 0.012

1.0

10/17/09 10,299,646.3 287.6 1,840.0 615.8 55 60.00 1.098 0.011

1.1

10/17/09 10,312,201.6 289.3 1,840.0 616.5 55 60.00 1.079 0.011

1.1

10/17/09 10,357,073.8 289.6 1,840.0 619.2 55 60.00 1.112 0.011

1.3

10/17/09 10,350,929.8 288.7 1,840.0 618.8 55 60.00 1.115 0.011

1.3

10/17/09 10,306,894.7 286.4 1,840.0 616.2 55 60.00 1.343 0.013

1.1

10/17/09 10,294,690.8 282.7 1,840.0 621.1 55 60.00 1.307 0.013

0.8

10/17/09 10,365,985.4 278.7 1,840.0 614.1 55 60.00 1.160 0.011

0.8

10/17/09 10,130,226.7 275.9 1,840.0 605.6 55 60.00 0.830 0.008

0.3

10/17/09 10,244,965.2 271.0 1,840.0 612.5 55 60.00 0.795 0.008

0.4

10/17/09 9,226,039.6 245.8 1,840.0 541.5 47 60.00 0.335 0.003

0.3

10/17/09 5,649,514.0 232.2 1,840.0 285.6 23 60.00 0.466 0.002

0.3

10/17/09 5,524,802.2 231.4 1,840.0 270.2 22 60.00 0.443 0.002

0.3

10/17/09 5,457,720.0 232.7 1,840.0 269.9 22 60.00 0.364 0.002

0.3

10/17/09 5,520,560.3 234.5 1,840.0 267.0 22 60.00 0.399 0.002

0.2

10/17/09 5,493,496.2 235.4 1,840.0 265.7 22 60.00 0.340 0.001

0.2

10/17/09 5,525,586.8 237.9 1,840.0 273.3 22 60.00 0.263 0.001

0.4

10/17/09 5,596,508.7 243.9 1,840.0 276.8 22 60.00 0.302 0.001

0.7

10/16/09 5,533,659.9 255.1 1,840.0 267.7 22 60.00 0.539 0.002

0.9

10/16/09 5,845,968.7 272.2 1,840.0 285.9 25 60.00 0.838 0.004

1.0

10/16/09 9,992,957.0 283.5 1,840.0 592.0 53 60.00 1.000 0.009

1.1

10/16/09 10,254,431.3 285.3 1,840.0 613.0 55 60.00 1.034 0.010

1.1

10/16/09 10,229,014.6 286.2 1,840.0 611.5 55 60.00 1.110 0.011

1.0

10/16/09 10,311,043.8 285.4 1,840.0 616.4 55 60.00 1.117 0.011

1.0

10/16/09 10,327,515.9 283.5 1,840.0 611.8 55 60.00 1.021 0.010

0.9

10/16/09 10,363,721.4 280.7 1,840.0 608.3 55 60.00 1.101 0.011

0.8

10/16/09 10,330,233.1 281.0 1,840.0 600.7 55 60.00 0.969 0.009

0.8

10/16/09 10,350,267.9 281.7 1,840.0 601.9 55 60.00 0.872 0.008

0.8

10/16/09 10,309,529.9 281.4 1,840.0 605.2 55 60.00 0.801 0.008

0.8

10/16/09 10,292,599.7 280.5 1,840.0 604.2 55 60.00 0.864 0.008

0.7

10/16/09 10,371,115.2 280.6 1,840.0 603.1 55 60.00 0.819 0.008

0.3

10/16/09 10,356,422.6 280.0 1,840.0 602.2 55 60.00 0.723 0.007

0.0

10/16/09 10,409,867.7 277.5 1,840.0 599.7 55 60.00 0.374 0.004

0.0

10/16/09 10,336,088.8 271.9 1,840.0 601.1 55 60.00 0.046 0.000

10/16/09 10,625,219.8 255.9 1,840.0 612.1 55 60.00 0.025 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00 1.1

1.0

10/19/09 10,445,795.9 286.7 1,840.0 613.1 55 60.00 1.159 0.011

0.9

10/19/09 10,473,392.4 284.4 1,840.0 614.7 55 60.00 1.066 0.010

0.8

10/19/09 10,437,909.6 277.3 1,840.0 618.3 55 60.00 0.925 0.009

0.5

10/19/09 10,328,002.5 262.5 1,840.0 606.2 54 60.00 0.888 0.009

0.6

10/19/09 7,335,965.5 237.4 1,840.0 394.7 34 60.00 0.628 0.004

0.5

10/19/09 5,592,290.9 236.6 1,840.0 267.4 22 60.00 0.758 0.003

0.5

10/19/09 5,593,808.6 237.7 1,840.0 267.5 22 60.00 0.646 0.003

0.4

10/19/09 5,594,779.7 239.5 1,840.0 270.6 22 60.00 0.599 0.003

0.7

10/19/09 5,566,176.4 244.3 1,840.0 266.2 22 60.00 0.533 0.002

0.8

10/18/09 5,531,908.8 253.9 1,840.0 267.6 22 60.00 0.947 0.004

1.1

10/18/09 5,587,959.4 269.1 1,840.0 267.3 23 60.00 1.068 0.005

1.1

10/18/09 9,581,121.1 282.6 1,840.0 551.9 50 60.00 1.197 0.011

1.2

10/18/09 10,312,025.7 284.8 1,840.0 610.9 55 60.00 1.145 0.011

1.2

10/18/09 10,324,577.0 286.3 1,840.0 611.6 55 60.00 1.215 0.012

1.2

10/18/09 10,321,659.2 286.3 1,840.0 611.5 55 60.00 1.265 0.012

1.3

10/18/09 10,301,164.8 284.8 1,840.0 610.2 55 60.00 1.239 0.012

1.3

10/18/09 10,278,742.4 282.4 1,840.0 614.5 55 60.00 1.368 0.013

1.2

10/18/09 10,229,568.7 281.5 1,840.0 611.6 55 60.00 1.372 0.013

1.1

10/18/09 10,266,416.6 284.4 1,840.0 608.1 55 60.00 1.234 0.012

1.1

10/18/09 10,297,991.4 286.2 1,840.0 615.6 55 60.00 1.191 0.012

1.1

10/18/09 10,270,658.6 286.1 1,840.0 614.0 55 60.00 1.202 0.012

1.2

10/18/09 10,294,077.9 284.4 1,840.0 615.4 55 60.00 1.125 0.011

1.2

10/18/09 10,253,332.0 281.4 1,840.0 613.0 55 60.00 1.263 0.012

1.1

10/18/09 10,192,871.4 279.2 1,840.0 614.9 55 60.00 1.242 0.012

1.0

10/18/09 10,256,555.8 279.1 1,840.0 613.2 55 60.00 1.100 0.011

0.7

10/18/09 10,236,438.3 274.4 1,840.0 611.9 55 60.00 1.068 0.010

0.4

10/18/09 10,403,949.0 256.1 1,840.0 616.3 54 60.00 0.767 0.008

0.5

10/18/09 6,250,114.6 232.4 1,840.0 326.1 27 60.00 0.420 0.002

0.6

10/18/09 5,456,791.9 233.7 1,840.0 269.9 22 60.00 0.660 0.003

0.6

10/18/09 5,449,638.6 234.5 1,840.0 266.6 22 60.00 0.757 0.003

0.7

10/18/09 5,503,657.8 236.9 1,840.0 266.2 22 60.00 0.766 0.003

0.9

10/18/09 5,438,909.8 241.4 1,840.0 266.0 22 60.00 0.855 0.004

0.9

10/18/09 6,317,927.2 251.7 1,840.0 267.8 22 60.00 1.340 0.006

1.1

10/17/09 6,384,232.2 269.6 1,840.0 270.6 23 60.00 1.277 0.006

1.1

10/17/09 9,687,073.6 283.4 1,840.0 563.3 51 60.00 1.149 0.010

1.0

10/17/09 10,282,795.7 283.9 1,840.0 614.7 55 60.00 1.095 0.011

10/17/09 10,283,836.9 286.0 1,840.0 614.8 55 60.00 1.057 0.010
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00 C

16:00 S S SC

17:00 C

18:00

19:00

20:00

21:00 0.9

0.9

10/20/09 10,019,236.4 282.4 1,840.0 620.7 55 60.00 0.885 0.009

0.9

10/20/09 10,008,714.7 283.2 1,840.0 620.1 55 60.00 0.928 0.009

1.1

10/20/09 9,998,961.5 282.3 1,840.0 624.9 55 60.00 0.941 0.009

1.3

10/20/09 9,931,994.6 279.9 1,840.0 620.8 55 60.00 1.111 0.011

1.5

10/20/09 9,804,556.3 278.4 1,840.0 618.1 55 60.00 1.288 0.013

1.6

10/20/09 9,877,861.9 279.8 1,840.0 622.7 55 60.00 1.456 0.014

1.3

10/20/09 9,849,678.2 279.9 1,840.0 621.0 55 60.00 1.613 0.016

1.1

10/20/09 9,885,067.1 278.9 1,840.0 617.8 55 60.00 1.296 0.013

1.1

10/20/09 9,832,951.6 278.1 1,840.0 614.6 55 60.00 1.141 0.011

1.1

10/20/09 9,815,472.2 278.4 1,840.0 618.8 55 60.00 1.073 0.011

1.1

10/20/09 9,757,722.7 278.4 1,840.0 615.2 55 60.00 1.036 0.010

1.2

10/20/09 9,810,054.1 277.6 1,840.0 618.5 55 60.00 1.051 0.010

1.2

10/20/09 9,785,099.7 275.9 1,840.0 616.9 55 60.00 1.172 0.012

1.0

10/20/09 9,791,530.0 275.5 1,840.0 617.3 55 60.00 1.156 0.011

0.7

10/20/09 9,777,232.0 274.2 1,840.0 616.4 55 60.00 0.955 0.009

0.2

10/20/09 9,735,563.9 267.3 1,840.0 619.1 55 60.00 0.659 0.007

0.5

10/20/09 8,890,013.4 244.8 1,840.0 560.5 49 60.00 0.213 0.002

0.4

10/20/09 5,513,500.1 235.7 1,840.0 269.7 22 60.00 0.636 0.003

0.4

10/20/09 5,522,170.4 240.5 1,840.0 264.1 22 60.00 0.496 0.002

0.3

10/20/09 5,510,980.7 247.5 1,840.0 266.6 22 60.00 0.491 0.002

0.5

10/20/09 5,597,388.6 259.2 1,840.0 267.7 22 60.00 0.346 0.001

0.7

10/20/09 7,265,706.8 276.2 1,840.0 375.1 35 60.00 0.597 0.004

1.3

10/19/09 9,706,114.5 283.7 1,840.0 611.9 55 60.00 0.665 0.006

1.4

10/19/09 10,383,780.5 287.9 1,840.0 615.1 55 60.00 1.390 0.014

1.5

10/19/09 10,416,129.3 288.7 1,840.0 617.0 55 60.00 1.525 0.015

1.6

10/19/09 10,432,491.0 288.4 1,840.0 618.0 55 60.00 1.611 0.016

1.6

10/19/09 10,411,595.0 286.9 1,840.0 616.8 55 60.00 1.672 0.016

1.3

10/19/09 10,411,769.6 285.7 1,840.0 616.8 55 60.00 1.737 0.017

1.3

10/19/09 10,428,221.5 287.1 1,840.0 612.1 55 60.00 1.416 0.014

1.3

10/19/09 10,417,481.3 287.5 1,840.0 611.4 55 60.00 1.366 0.013

1.3

10/19/09 10,421,200.6 286.8 1,840.0 611.7 55 60.00 1.415 0.014

1.4

10/19/09 10,533,170.5 287.4 1,840.0 624.0 56 60.00 1.357 0.014

1.4

10/19/09 10,598,565.3 290.4 1,840.0 627.9 56 60.00 1.448 0.015

1.5

10/19/09 10,659,345.2 290.8 1,840.0 631.4 56 60.00 1.467 0.015

1.4

10/19/09 10,645,873.8 288.5 1,840.0 630.7 56 60.00 1.559 0.016

1.2

10/19/09 10,503,623.8 286.4 1,840.0 622.2 55 60.00 1.491 0.015

10/19/09 10,477,098.1 287.2 1,840.0 615.0 55 60.00 1.323 0.013
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

22:00

23:00

00:00

01:00 C

02:00 C C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C S S S

03:00 S S S

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00 0.9

0.9

10/22/09 9,806,514.3 274.6 1,840.0 559.6 50 60.00 1.026 0.009

0.9

10/22/09 9,677,922.0 273.1 1,840.0 557.5 50 60.00 1.029 0.009

0.8

10/22/09 9,625,015.7 272.7 1,840.0 559.7 50 60.00 1.011 0.009

0.5

10/22/09 9,505,567.0 268.5 1,840.0 563.1 50 60.00 0.883 0.008

0.4

10/22/09 9,418,306.9 249.3 1,840.0 547.7 47 60.00 0.525 0.005

1.2

10/22/09 5,838,875.1 234.5 1,840.0 304.6 26 60.00 0.527 0.003

0.8

10/22/09 5,624,066.8 234.5 1,840.0 287.3 25 60.00 1.500 0.007

0.8

10/22/09 5,597,747.7 236.8 1,840.0 286.0 25 60.00 1.008 0.005

0.4

10/22/09 5,609,548.0 239.8 1,840.0 286.6 25 60.00 1.009 0.005

0.4

10/22/09 5,639,547.8 242.4 1,840.0 288.1 25 60.00 0.512 0.002

0.4

10/22/09 5,668,198.6 248.0 1,840.0 289.6 25 60.00 0.440 0.002

0.9

10/21/09 5,818,722.7 261.2 1,840.0 287.8 25 60.00 0.543 0.003

1.0

10/21/09 7,279,481.5 281.0 1,840.0 371.9 35 60.00 1.055 0.006

1.1

10/21/09 10,336,400.5 288.5 1,840.0 612.3 55 60.00 1.107 0.011

1.2

10/21/09 10,381,644.5 288.4 1,840.0 609.4 55 60.00 1.193 0.012

1.2

10/21/09 10,383,336.3 286.5 1,840.0 609.4 55 60.00 1.248 0.012

0.9

10/21/09 10,416,199.4 284.6 1,840.0 611.4 55 60.00 1.258 0.012

0.7

10/21/09 10,306,349.1 285.1 1,840.0 604.9 55 60.00 0.963 0.009

0.7

10/21/09 10,106,414.0 285.9 1,840.0 615.1 55 60.00 0.763 0.008

0.6

10/21/09 10,140,896.7 285.3 1,840.0 617.3 55 60.00 0.718 0.007

0.8

10/21/09 9,846,750.1 283.1 1,840.0 599.4 53 60.00 0.658 0.006

0.7

10/21/09 9,961,822.8 282.0 1,840.0 595.6 54 60.00 0.848 0.008

0.6

10/21/09 10,090,535.3 281.7 1,840.0 614.2 55 60.00 0.733 0.007

0.6

10/21/09 10,073,443.1 282.4 1,840.0 618.6 55 60.00 0.628 0.006

0.7

10/21/09 10,011,118.6 282.8 1,840.0 625.7 55 60.00 0.581 0.006

0.8

10/21/09 10,035,057.6 282.8 1,840.0 638.1 55 60.00 0.707 0.007

0.8

10/21/09 10,290,037.4 283.7 1,840.0 620.8 55 60.00 0.823 0.008

0.8

10/21/09 10,114,161.3 285.4 1,840.0 610.1 54 60.00 0.790 0.008

0.9

10/21/09 10,071,731.0 286.3 1,840.0 607.6 54 60.00 0.860 0.008

0.9

10/21/09 10,138,296.2 285.7 1,840.0 611.6 54 60.00 0.927 0.009

0.8

10/21/09 10,102,970.3 283.2 1,840.0 620.5 55 60.00 0.966 0.010

0.8

10/21/09 10,093,762.6 281.3 1,840.0 614.4 55 60.00 0.869 0.009

0.5

10/21/09 10,071,656.7 280.3 1,840.0 613.1 55 60.00 0.819 0.008

0.6

10/21/09 10,166,758.7 273.8 1,840.0 624.4 55 60.00 0.496 0.005

0.7

10/21/09 7,042,494.4 268.2 1,840.0 367.4 32 60.00 0.702 0.004

0.9

10/20/09 8,934,190.6 281.2 1,840.0 514.7 46 60.00 0.809 0.007

10/20/09 10,077,416.4 281.3 1,840.0 618.9 55 60.00 0.882 0.009
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00

00:00

01:00

02:00 C

03:00

04:00 C

05:00 C C

06:00

07:00

08:00

09:00

10:00

11:00

12:00

13:00

14:00

15:00

16:00

17:00

18:00

19:00

20:00

21:00

22:00

23:00 0.3

0.2

10/23/09 4,380,299.9 240.0 1,840.0 166.6 13 60.00 0.480 0.001

0.5

10/23/09 4,903,624.1 256.0 1,840.0 191.9 17 60.00 0.374 0.001

0.7

10/23/09 7,333,403.0 270.7 1,840.0 402.5 36 60.00 0.551 0.004

0.7

10/23/09 9,241,623.8 277.8 1,840.0 542.5 48 60.00 0.735 0.006

0.7

10/23/09 9,512,959.3 279.5 1,840.0 563.5 50 60.00 0.713 0.006

0.7

10/23/09 9,584,141.7 280.5 1,840.0 562.5 50 60.00 0.740 0.007

0.7

10/23/09 9,700,624.6 280.9 1,840.0 564.1 50 60.00 0.713 0.006

0.7

10/23/09 9,759,409.6 279.7 1,840.0 562.2 50 60.00 0.747 0.007

0.6

10/23/09 9,751,402.4 277.5 1,840.0 561.7 50 60.00 0.730 0.007

0.7

10/23/09 9,854,116.6 276.5 1,840.0 557.0 50 60.00 0.713 0.006

0.8

10/23/09 9,866,759.8 276.2 1,840.0 552.3 50 60.00 0.733 0.006

0.8

10/23/09 9,857,597.9 275.5 1,840.0 551.8 50 60.00 0.849 0.007

0.9

10/23/09 9,769,411.4 273.7 1,840.0 552.2 50 60.00 0.926 0.008

0.8

10/23/09 9,743,614.9 272.7 1,840.0 550.7 50 60.00 0.979 0.009

0.7

10/23/09 9,767,175.7 273.6 1,840.0 552.0 50 60.00 0.876 0.008

0.7

10/23/09 9,791,022.4 272.5 1,840.0 553.4 50 60.00 0.753 0.007

0.7

10/23/09 9,844,047.1 269.7 1,840.0 556.4 50 60.00 0.721 0.006

0.7

10/23/09 9,723,244.4 263.6 1,840.0 554.8 50 60.00 0.742 0.007

0.3

10/23/09 9,901,404.4 246.1 1,840.0 559.6 50 60.00 0.730 0.007

0.2

10/23/09 6,306,656.4 226.1 1,840.0 322.2 28 60.00 0.314 0.002

0.2

10/23/09 5,542,664.8 226.5 1,840.0 262.1 23 60.00 0.310 0.001

0.3

10/23/09 5,548,862.6 228.0 1,840.0 268.4 23 60.00 0.300 0.001

0.7

10/23/09 5,537,926.6 230.9 1,840.0 267.9 23 60.00 0.332 0.001

0.7

10/23/09 5,484,843.9 237.7 1,840.0 268.3 23 60.00 0.842 0.004

0.8

10/22/09 5,624,022.7 252.5 1,840.0 265.9 23 60.00 0.935 0.004

0.9

10/22/09 8,328,554.6 267.6 1,840.0 475.3 43 60.00 0.921 0.007

0.9

10/22/09 9,473,957.2 270.5 1,840.0 561.2 50 60.00 0.922 0.008

1.0

10/22/09 9,587,208.3 272.5 1,840.0 562.7 50 60.00 0.909 0.008

1.0

10/22/09 9,610,015.0 272.8 1,840.0 558.8 50 60.00 1.064 0.010

0.9

10/22/09 9,598,534.6 272.2 1,840.0 563.4 50 60.00 1.019 0.009

0.8

10/22/09 9,545,692.1 271.4 1,840.0 560.3 50 60.00 0.991 0.009

0.8

10/22/09 9,562,910.2 273.2 1,840.0 561.3 50 60.00 0.863 0.008

0.8

10/22/09 9,484,827.5 273.9 1,840.0 556.7 50 60.00 0.796 0.007

0.9

10/22/09 9,561,203.1 273.7 1,840.0 561.2 50 60.00 0.837 0.008

0.9

10/22/09 9,577,352.9 273.6 1,840.0 556.9 50 60.00 0.923 0.008

0.9

10/22/09 9,658,247.9 274.5 1,840.0 556.4 50 60.00 0.932 0.008

10/22/09 9,742,772.3 274.9 1,840.0 556.0 50 60.00 0.934 0.008
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

00:00

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F 0.0 F

0.0

10/25/09 1,953,650.3 105.8 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 1,965,354.7 107.5 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 1,984,656.2 109.5 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 2,036,347.0 111.8 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 2,063,057.5 114.3 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 2,094,445.7 116.9 1,840.0 0.0 0 0.00 0.000

0.2

10/25/09 2,045,767.4 119.4 1,840.0 0.0 0 0.00 0.000

2.4

10/25/09 2,094,971.7 122.1 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 2,113,284.2 125.3 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 2,154,930.8 128.7 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 3,433,869.1 132.5 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 2,181,745.8 136.3 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 2,144,965.0 139.9 1,840.0 0.0 0 0.00 0.000

0.0

10/24/09 2,040,695.1 143.3 1,840.0 0.0 0 0.00 0.000

0.0

10/24/09 2,118,723.4 146.7 1,840.0 0.0 0 0.00 0.000

0.0

10/24/09 2,046,785.9 149.1 1,840.0 0.0 0 0.00 0.000

0.0

10/24/09 1,927,802.7 151.1 1,840.0 0.0 0 0.00 0.000

0.0

10/24/09 1,901,807.2 152.7 1,840.0 0.0 0 0.00 0.000

0.0

10/24/09 1,931,068.6 153.7 1,840.0 0.0 0 0.00 0.000

0.0

10/24/09 1,918,390.9 153.3 1,840.0 0.0 0 0.00 0.000

0.0

10/24/09 1,897,556.9 151.7 1,840.0 0.0 0 0.00 0.000

0.0

10/24/09 1,894,321.1 149.4 1,840.0 0.0 0 0.00 0.000

0.0

10/24/09 1,914,528.1 147.3 1,840.0 0.0 0 0.00 0.000

0.0

10/24/09 1,918,707.3 146.7 1,840.0 0.0 0 0.00 0.000

0.0

10/24/09 1,960,622.5 148.5 1,840.0 0.0 0 0.00 0.000

0.0

10/24/09 2,623,975.6 154.0 1,840.0 0.0 0 0.00 0.000 0.000

0.0

10/24/09 2,661,595.8 151.9 1,840.0 0.0 0 0.00 0.000 0.000

0.0

10/24/09 5,760,315.3 159.8 1,840.0 0.0 0 0.00 0.000 0.000

0.0

10/24/09 6,093,870.6 165.3 1,840.0 0.0 0 0.00 0.000 0.000

0.0

10/24/09 5,930,759.8 170.8 1,840.0 0.0 0 0.00 0.000 0.000

0.2

10/24/09 5,861,340.1 179.2 1,840.0 0.0 0 0.00 0.000 0.000

1.9

10/24/09 5,717,779.3 184.7 1,840.0 3.1 0 0.00 47.748 0.000

0.0

10/24/09 5,364,984.7 188.9 1,840.0 2.9 0 0.00 365.326 0.000

0.0

10/24/09 5,301,759.6 195.9 1,840.0 2.9 0 0.00 0.000 0.000

0.1

10/24/09 5,524,486.0 205.1 1,840.0 84.1 0 0.00 0.014 0.000

0.3

10/24/09 5,208,693.4 211.6 1,840.0 2.8 0 0.00 6.545 0.000

10/24/09 4,403,741.0 231.3 1,840.0 119.7 5 13.00 0.592 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F 0.0 F

0.0

10/27/09 2,102,828.0 82.2 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 2,098,746.9 82.5 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 2,078,681.8 82.8 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 2,103,967.7 83.3 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,968,147.6 83.5 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,883,253.3 83.9 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,780,337.0 84.2 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,830,634.7 84.7 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,809,946.5 85.1 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,811,580.4 85.5 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,801,157.1 85.7 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,803,142.4 86.1 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,762,877.1 86.3 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,763,756.1 86.7 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,763,340.7 87.2 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,747,447.9 87.7 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,733,744.0 88.1 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,710,934.4 88.4 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,746,303.4 88.8 1,840.0 0.0 0 0.00 0.000

0.2

10/26/09 1,750,231.2 89.5 1,840.0 0.0 0 0.00 0.000

2.4

10/26/09 1,830,585.8 90.2 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,849,272.2 91.0 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,926,158.0 91.7 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 3,289,812.6 92.3 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 1,976,917.8 92.7 1,840.0 0.0 0 0.00 0.000

0.0

10/26/09 2,021,041.8 93.1 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 2,009,253.2 93.5 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 2,007,042.3 94.1 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 1,819,154.4 94.6 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 1,767,748.9 95.2 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 1,720,020.0 95.9 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 1,736,066.3 96.6 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 1,819,060.3 97.8 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 1,863,541.2 99.0 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 1,916,020.9 100.4 1,840.0 0.0 0 0.00 0.000

0.0

10/25/09 1,950,190.1 102.2 1,840.0 0.0 0 0.00 0.000

10/25/09 1,996,484.9 104.0 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F FC

02:00 FC F F F F F F F FC

03:00 F F F F F F F F F

04:00 F F F F F F F F FC

05:00 FC F F F F F F F FC

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F 0.0 F

0.0

10/28/09 1,685,146.7 78.1 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,700,983.8 78.0 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,668,222.7 77.9 1,840.0 10.0 0 0.00 0.000 0.000

0.0

10/28/09 1,662,070.9 77.9 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,652,034.6 77.8 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,643,895.3 77.6 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,670,450.3 77.1 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,654,209.4 76.5 1,840.0 0.0 0 0.00 0.000

0.2

10/28/09 1,634,867.0 76.4 1,840.0 0.0 0 0.00 0.000

2.4

10/28/09 1,643,274.5 76.3 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,814,930.4 76.1 1,840.0 0.0 0 0.00 0.000

1.4

10/28/09 1,821,190.2 76.1 1,840.0 0.0 0 0.00 0.000

2.4

10/28/09 3,287,221.8 76.0 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,864,333.9 75.9 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,875,089.8 75.8 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,784,078.2 75.8 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,882,130.5 75.9 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,750,622.9 76.0 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,734,195.9 76.2 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,730,679.1 76.5 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,732,745.0 76.7 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,710,120.3 77.1 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,711,048.3 77.6 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,705,073.8 78.2 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,726,265.4 78.8 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,742,088.7 79.1 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,704,898.4 79.3 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,725,143.1 79.7 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,772,952.3 79.4 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,827,207.0 78.9 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,833,232.1 78.6 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 1,879,605.6 78.8 1,840.0 0.0 0 0.00 0.000

0.2

10/27/09 1,875,872.7 79.4 1,840.0 0.0 0 0.00 0.000

2.4

10/27/09 2,110,316.0 80.1 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 2,191,060.2 80.6 1,840.0 0.0 0 0.00 0.000

0.0

10/27/09 2,112,971.6 81.2 1,840.0 0.0 0 0.00 0.000

10/27/09 3,434,293.1 81.8 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F 0.0 F

0.0

10/30/09 1,743,872.6 71.3 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 3,204,149.1 71.5 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,790,393.0 71.6 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,759,486.3 71.8 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,708,903.4 72.0 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,687,256.9 72.1 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,669,488.6 72.4 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,560,172.1 72.6 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,491,396.8 72.7 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,485,837.8 72.8 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,485,946.6 73.1 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,510,507.2 73.5 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,528,540.2 74.0 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,533,633.5 74.2 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,537,143.8 74.5 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,547,060.8 74.9 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,537,584.6 75.1 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,542,824.1 75.3 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,542,218.3 75.6 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,529,220.7 76.1 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,534,461.9 76.7 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,520,176.9 76.9 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,528,105.3 77.0 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,566,064.8 77.1 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,690,925.4 77.1 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 3,145,560.7 77.0 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,732,164.7 77.0 1,840.0 0.0 0 0.00 0.000

0.0

10/29/09 1,728,881.1 76.9 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,728,635.2 77.0 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,702,690.1 77.0 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,551,579.9 77.0 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,515,028.2 77.1 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,511,430.8 77.2 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,479,589.2 77.3 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,459,043.8 77.6 1,840.0 0.0 0 0.00 0.000

0.0

10/28/09 1,448,654.5 77.7 1,840.0 0.0 0 0.00 0.000

10/28/09 1,519,241.7 77.9 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F 0.0 F

0.0

10/31/09 1,631,654.4 67.2 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,664,349.7 67.2 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,667,567.5 67.2 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,675,838.3 67.3 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,645,841.9 67.4 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,647,733.8 67.6 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,638,217.3 67.7 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,582,901.0 68.1 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,625,831.8 68.4 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,597,487.9 68.4 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,604,361.3 68.4 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,718,535.4 68.6 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,796,183.0 68.7 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,800,430.2 68.7 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 3,229,206.1 68.6 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,794,341.8 68.6 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,803,170.0 68.4 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,678,212.5 68.1 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,688,947.4 68.1 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,667,081.9 68.3 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,624,600.0 68.7 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,507,266.6 69.4 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,460,293.4 70.0 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,451,630.2 70.7 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,521,000.5 72.0 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,438,313.0 72.8 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,495,043.0 72.7 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,422,238.9 72.6 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,442,530.8 72.2 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,416,436.2 71.7 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,487,867.1 71.5 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,493,435.3 71.3 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,446,836.5 71.1 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,522,549.1 70.9 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,511,187.0 70.8 1,840.0 0.0 0 0.00 0.000

0.0

10/30/09 1,526,469.1 71.0 1,840.0 0.0 0 0.00 0.000

10/30/09 1,681,115.4 71.1 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F 0.0 F

0.0

11/02/09 1,822,726.2 63.2 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 1,847,018.8 63.2 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 1,858,430.3 63.3 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 3,244,517.9 63.5 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 1,806,955.2 63.7 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 1,837,712.9 64.1 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,827,482.3 64.1 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,799,893.9 64.0 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,813,192.3 63.8 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,674,795.0 63.6 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,648,931.4 63.7 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,625,346.3 63.9 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,636,542.5 64.2 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,769,941.5 64.5 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,838,484.2 64.8 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,788,802.5 64.9 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,756,131.8 65.0 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,723,946.0 65.1 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,752,183.8 65.1 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,689,869.8 64.8 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,659,309.1 64.3 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,688,853.8 63.9 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,816,260.5 64.0 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,891,795.1 64.4 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,815,544.2 64.7 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,826,168.6 65.2 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,854,415.0 65.6 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 3,284,533.9 65.9 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,804,492.2 66.2 1,840.0 0.0 0 0.00 0.000

0.0

11/01/09 1,819,873.4 66.6 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,826,682.3 66.8 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,819,410.4 66.9 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,699,224.8 67.0 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,648,425.5 67.1 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,634,739.0 67.2 1,840.0 0.0 0 0.00 0.000

0.0

10/31/09 1,645,967.5 67.2 1,840.0 0.0 0 0.00 0.000

10/31/09 1,651,989.7 67.3 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F 0.0 F

0.0

11/03/09 2,291,750.2 68.7 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,320,557.7 68.5 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,381,215.0 69.3 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,496,926.1 70.3 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,356,983.4 70.1 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,368,777.4 69.8 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,575,781.6 69.4 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,446,698.7 68.6 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,392,012.0 67.8 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,426,360.7 67.0 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,467,274.9 66.4 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,498,846.0 66.2 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,485,658.4 66.4 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,567,215.7 66.9 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,707,808.1 67.3 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,745,333.9 67.8 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 3,840,847.1 68.4 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,661,628.6 69.0 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,665,322.1 69.7 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,692,660.0 70.1 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,504,769.3 70.3 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,407,721.9 70.6 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,394,803.7 70.7 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,316,485.3 70.8 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,286,595.0 70.8 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,296,508.3 70.8 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,427,375.8 70.6 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,460,552.8 70.4 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,400,360.9 69.9 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,336,745.5 69.4 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,312,217.2 69.1 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,298,156.0 68.7 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,317,563.3 67.6 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,331,511.9 66.2 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 2,094,501.2 64.4 1,840.0 0.0 0 0.00 0.000

0.0

11/02/09 1,758,714.5 63.5 1,840.0 0.0 0 0.00 0.000

11/02/09 1,696,072.6 63.2 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F 0.0 F

0.0

11/05/09 2,551,375.1 70.0 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,648,614.8 70.2 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,817,647.6 70.4 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,879,256.9 70.6 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,819,085.1 70.8 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 3,897,996.2 71.0 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,800,402.1 70.9 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,758,957.9 70.8 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,766,803.9 70.6 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,575,817.1 70.3 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,539,604.4 70.0 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,501,939.7 69.5 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,464,124.5 68.9 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,458,791.3 68.7 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,377,169.0 68.7 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,502,041.3 68.5 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,528,063.1 68.2 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,537,471.5 67.8 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,392,672.6 66.9 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,372,394.0 66.4 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,329,273.9 66.0 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,318,941.4 65.9 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,377,981.5 65.8 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,394,413.4 65.9 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,369,117.3 65.9 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,361,847.6 66.9 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,538,252.9 68.2 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,629,874.0 68.4 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,688,707.0 68.0 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 3,815,783.6 67.4 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,655,280.6 66.8 1,840.0 0.0 0 0.00 0.000

0.0

11/04/09 2,625,758.9 66.2 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,664,789.7 65.9 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,521,600.9 66.2 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,323,448.1 66.9 1,840.0 0.0 0 0.00 0.000

0.0

11/03/09 2,309,984.7 68.0 1,840.0 0.0 0 0.00 0.000

11/03/09 2,282,074.9 68.8 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F 0.0 F

0.0

11/06/09 2,415,402.1 63.2 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,354,715.3 63.0 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,389,367.4 62.9 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,364,381.2 62.9 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,451,551.4 63.0 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,692,852.4 63.2 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,549,487.4 63.2 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,560,536.8 63.3 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,551,519.5 63.5 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,549,211.2 63.6 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,578,008.9 63.7 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,595,230.5 64.1 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,517,737.2 64.5 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,508,774.0 64.9 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,634,778.9 65.3 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,815,812.8 66.0 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,829,905.7 66.7 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,862,432.6 67.3 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 3,938,117.9 68.0 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,857,682.9 68.7 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,853,654.3 69.5 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,837,826.6 70.4 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,859,392.3 71.3 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,619,444.9 72.2 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,458,091.6 73.0 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,454,158.5 74.4 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,401,405.7 75.0 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,332,567.7 74.9 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,404,317.4 74.7 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,520,115.8 74.4 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,514,380.7 74.0 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,486,733.2 73.5 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,507,456.4 72.9 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,519,046.4 72.2 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,505,122.5 71.4 1,840.0 0.0 0 0.00 0.000

0.0

11/05/09 2,556,896.5 70.7 1,840.0 0.0 0 0.00 0.000

11/05/09 2,562,261.9 70.2 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F 0.0 F

0.0

11/08/09 2,705,992.9 77.6 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,711,476.8 77.7 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,714,877.1 77.4 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,706,759.5 77.5 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,718,089.7 77.8 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,698,523.2 78.1 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,670,930.2 78.4 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 3,809,027.7 78.5 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,657,772.6 78.5 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,646,901.0 78.6 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,603,859.8 78.7 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,605,980.3 78.7 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,537,252.9 78.6 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,531,836.5 78.8 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,524,876.8 79.0 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,550,898.0 79.0 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,521,078.3 78.5 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,505,487.2 77.8 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,509,215.4 77.0 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,511,015.3 76.1 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,541,778.5 75.2 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,571,693.8 74.2 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,595,015.9 72.9 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,616,970.9 71.2 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,618,340.9 69.3 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,653,183.8 67.1 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,686,949.0 65.7 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,696,318.8 65.2 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,704,625.7 65.0 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,702,901.9 64.8 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,733,170.1 64.7 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 3,845,090.3 64.6 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,720,787.7 64.4 1,840.0 0.0 0 0.00 0.000

0.0

11/07/09 2,761,899.2 64.2 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,761,979.9 64.1 1,840.0 0.0 0 0.00 0.000

0.0

11/06/09 2,722,348.0 63.9 1,840.0 0.0 0 0.00 0.000

11/06/09 2,536,187.5 63.5 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F 0.0 F

0.0

11/09/09 2,617,112.0 75.4 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,569,977.8 75.8 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,551,127.4 76.1 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,535,140.1 76.4 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,579,040.9 76.7 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,573,045.4 77.0 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,543,597.4 77.4 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,580,869.2 77.7 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,685,864.4 77.9 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,688,689.0 78.0 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,663,933.5 78.0 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,650,419.3 77.7 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,651,445.3 77.4 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,660,538.5 77.3 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,626,749.5 77.3 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,629,419.1 77.4 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,577,943.0 77.5 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,550,864.9 77.1 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,570,221.7 76.3 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,586,492.3 75.3 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 3,728,486.2 73.9 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,583,187.4 72.8 1,840.0 0.0 0 0.00 0.000

0.0

11/09/09 2,579,924.4 72.5 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,572,610.0 72.4 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,578,741.5 72.2 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,469,694.8 72.1 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,320,959.1 72.2 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,321,600.8 72.6 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,327,152.1 73.0 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,421,782.9 73.6 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,613,679.9 74.5 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,640,863.2 75.3 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,681,171.0 75.9 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,745,684.8 76.2 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,706,771.3 76.6 1,840.0 0.0 0 0.00 0.000

0.0

11/08/09 2,637,983.0 77.1 1,840.0 0.0 0 0.00 0.000

11/08/09 2,687,570.0 77.3 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F 0.0 F

0.0

11/11/09 2,889,204.0 69.3 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,897,344.8 69.3 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,900,330.6 69.4 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,910,724.4 69.3 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,894,652.0 69.2 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,901,373.5 70.2 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,796,875.8 71.7 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,762,326.6 72.9 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,689,780.5 73.1 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 3,821,676.8 73.3 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,748,433.6 73.3 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,689,329.6 73.3 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,735,832.2 73.3 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,692,792.5 73.2 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,705,176.4 73.3 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,689,872.2 73.5 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,687,268.8 73.8 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,714,103.2 73.9 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,706,562.6 74.1 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,661,872.6 74.2 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,697,296.2 74.1 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,700,860.2 74.1 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,695,938.0 74.0 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,669,156.5 73.9 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,714,025.6 73.7 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,735,486.6 73.3 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,722,118.4 73.0 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,721,499.7 73.1 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,720,998.8 73.0 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,742,322.9 73.1 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,709,081.0 73.2 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,725,594.5 73.2 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,746,534.8 73.4 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 3,881,863.3 73.9 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,741,826.6 74.4 1,840.0 0.0 0 0.00 0.000

0.0

11/10/09 2,773,230.0 74.8 1,840.0 0.0 0 0.00 0.000

11/09/09 2,596,460.9 75.0 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F 0.0 F

0.0

11/13/09 2,780,249.0 61.9 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,765,553.8 61.9 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,712,891.3 62.0 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,685,439.0 62.1 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,674,321.6 62.2 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,695,239.6 62.2 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,690,028.8 62.4 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,686,744.3 62.7 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,703,595.6 63.3 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,725,480.7 63.7 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,702,606.5 64.1 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,715,063.1 64.5 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,763,811.7 64.8 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,769,656.4 65.0 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,784,741.9 65.2 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,792,553.0 65.1 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,808,910.3 64.8 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,806,670.8 63.6 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,770,992.8 63.6 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,824,560.6 64.0 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,751,746.8 64.8 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,804,991.1 65.5 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 3,880,827.1 66.3 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,750,323.7 66.9 1,840.0 0.0 0 0.00 0.000

0.0

11/12/09 2,793,586.0 67.4 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,773,621.2 68.1 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,708,215.3 68.5 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,710,825.2 68.9 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,677,215.7 68.7 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,718,511.8 68.0 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,693,906.5 67.9 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,673,333.0 68.3 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,651,395.9 68.8 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,674,358.8 69.0 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,825,409.8 69.0 1,840.0 0.0 0 0.00 0.000

0.0

11/11/09 2,900,515.8 68.9 1,840.0 0.0 0 0.00 0.000

11/11/09 2,896,751.8 69.1 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F 0.0 F

0.0

11/14/09 2,550,664.0 67.1 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,562,695.5 66.9 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,577,211.0 66.5 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,579,204.1 65.6 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,630,895.0 64.5 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,655,194.9 63.9 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,661,412.0 63.7 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,668,924.8 63.4 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,672,325.6 63.2 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,690,060.5 63.2 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,682,766.0 63.2 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 3,796,821.0 63.1 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,706,064.9 63.1 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,644,857.7 63.0 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,666,541.9 63.0 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,645,444.0 62.6 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,617,972.8 62.2 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,603,985.3 62.0 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,610,926.0 61.7 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,611,892.3 61.5 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,620,902.3 61.4 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,626,356.5 61.5 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,643,601.8 61.8 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,635,563.1 62.0 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,649,957.5 62.1 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,671,234.6 61.8 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,695,788.7 61.5 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,698,439.7 61.0 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,684,493.5 60.6 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,663,934.8 60.7 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,677,000.6 61.0 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,659,523.7 61.1 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,809,178.1 61.1 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,735,179.8 61.2 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 2,774,818.8 61.3 1,840.0 0.0 0 0.00 0.000

0.0

11/13/09 3,883,563.5 61.4 1,840.0 0.0 0 0.00 0.000

11/13/09 2,753,400.4 61.7 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F 0.0 F

0.0

11/16/09 3,923,562.3 67.8 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,743,525.4 68.0 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,778,315.1 68.2 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,761,120.0 68.4 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,579,009.9 68.6 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,502,415.2 68.8 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,391,465.6 69.2 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,425,068.6 69.6 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,448,280.9 69.9 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,445,363.9 70.4 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,607,441.4 71.1 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,650,792.8 71.4 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,671,753.3 71.5 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,639,642.6 71.4 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,720,688.8 71.3 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,747,347.8 71.0 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,755,006.9 70.4 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,787,186.9 69.8 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,790,573.7 69.4 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,738,628.6 69.6 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,744,016.2 70.0 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,782,671.7 70.5 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,748,005.0 70.8 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,798,025.0 71.1 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 3,878,678.8 71.3 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,700,518.4 71.5 1,840.0 0.0 0 0.00 0.000

0.0

11/15/09 2,772,657.5 71.8 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,676,598.6 72.0 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,670,625.0 72.1 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,635,762.9 72.0 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,626,557.4 71.5 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,609,105.9 70.7 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,573,711.5 69.9 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,565,853.4 69.0 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,566,636.3 68.0 1,840.0 0.0 0 0.00 0.000

0.0

11/14/09 2,554,776.1 67.6 1,840.0 0.0 0 0.00 0.000

11/14/09 2,545,922.3 67.3 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F 0.0 F

0.0

11/17/09 2,468,749.4 72.4 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,490,294.0 72.8 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,502,461.4 72.8 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,485,240.1 72.6 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,450,912.5 72.2 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,469,313.1 71.7 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,458,536.9 71.3 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,443,498.0 71.1 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,435,090.3 71.0 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,630,129.3 71.2 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,765,427.6 71.3 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,766,663.5 71.3 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,667,721.8 71.3 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 3,780,529.2 71.4 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,668,377.2 71.7 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,628,709.6 71.9 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,691,805.1 71.9 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,676,653.0 71.6 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,538,800.2 71.4 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,569,757.7 71.1 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,511,538.5 70.7 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,483,376.0 70.4 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,512,516.6 70.1 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,728,753.2 70.2 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,783,800.7 70.0 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,831,946.7 69.6 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,781,447.5 69.0 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,825,548.9 68.5 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,749,354.9 67.8 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,653,651.3 67.3 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,654,435.7 67.0 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,682,216.1 66.5 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,763,043.5 66.8 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,835,086.0 67.2 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,909,996.3 67.3 1,840.0 0.0 0 0.00 0.000

0.0

11/16/09 2,878,602.7 67.5 1,840.0 0.0 0 0.00 0.000

11/16/09 2,906,310.9 67.7 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F 0.0 F

0.0

11/19/09 2,732,545.3 69.6 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,729,574.4 69.6 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 3,870,156.8 69.4 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,773,228.8 69.5 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,681,420.0 69.9 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,614,907.0 70.6 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,772,394.5 70.8 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,465,811.7 71.0 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,379,879.1 71.2 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,372,868.1 71.5 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,373,570.5 71.7 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,373,068.4 72.0 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,337,069.4 72.4 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,343,273.4 72.8 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,377,810.8 73.5 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,323,596.1 73.8 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,376,100.9 73.9 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,373,477.5 73.8 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,366,532.5 73.8 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,380,622.1 73.4 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,376,311.6 73.0 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,357,354.9 73.0 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,564,469.8 73.1 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,781,611.1 73.1 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,807,930.4 73.0 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,842,778.2 72.8 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 3,882,466.6 72.6 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,862,025.3 72.6 1,840.0 0.0 0 0.00 0.000

0.0

11/18/09 2,804,621.7 72.4 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,759,645.9 72.3 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,758,596.6 71.9 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,568,666.7 71.4 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,447,251.4 71.1 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,441,560.1 71.1 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,457,368.1 71.4 1,840.0 0.0 0 0.00 0.000

0.0

11/17/09 2,444,290.6 71.6 1,840.0 0.0 0 0.00 0.000

11/17/09 2,442,831.6 71.9 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F 0.0 F

0.0

11/20/09 2,369,025.9 74.5 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,422,142.2 74.3 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,414,156.9 73.9 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,422,856.3 73.4 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,336,345.6 73.0 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,344,893.0 72.6 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,424,867.3 72.3 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,401,246.7 72.0 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,461,320.3 71.8 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,486,173.6 71.7 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,531,642.4 71.7 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,585,821.5 71.8 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,777,042.3 72.0 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,807,037.5 72.1 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,766,593.1 72.0 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 3,848,485.6 72.2 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,781,948.3 72.2 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,814,441.0 72.1 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,725,515.4 71.7 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,631,530.0 71.3 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,515,854.0 70.9 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,473,241.5 70.7 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,486,577.6 70.8 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,451,040.2 70.9 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,430,541.5 70.8 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,443,239.6 70.7 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,444,459.9 70.6 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,410,315.9 70.4 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,487,157.9 70.2 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,600,045.4 70.0 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,459,956.9 69.7 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,488,455.0 69.8 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,476,370.9 69.8 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,446,537.5 69.8 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,415,768.7 69.8 1,840.0 0.0 0 0.00 0.000

0.0

11/19/09 2,465,900.8 69.8 1,840.0 0.0 0 0.00 0.000

11/19/09 2,643,138.7 69.7 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F 0.0 F

0.0

11/22/09 2,820,587.7 65.4 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,830,638.5 65.7 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,839,576.9 65.9 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,830,795.4 66.2 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 3,908,493.1 66.5 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,837,473.1 66.7 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,735,386.5 66.5 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,753,705.1 66.6 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,796,053.1 66.8 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,833,409.5 67.2 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,779,375.3 67.5 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,586,986.9 67.8 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,573,054.4 68.4 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,530,592.1 69.0 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,739,315.0 69.8 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,805,421.8 70.6 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,801,160.6 71.3 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,788,327.5 72.2 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,798,410.6 73.0 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,671,849.4 73.6 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,451,573.5 73.7 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,344,601.5 73.3 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,436,147.9 72.9 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,663,270.8 73.1 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,644,591.1 73.4 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,771,957.3 73.6 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,803,986.1 73.7 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,808,166.9 74.0 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 3,868,120.6 74.1 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,772,833.0 74.4 1,840.0 0.0 0 0.00 0.000

0.0

11/21/09 2,798,729.2 74.6 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,613,092.0 74.6 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,489,587.3 74.9 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,474,643.2 74.9 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,459,916.3 74.8 1,840.0 0.0 0 0.00 0.000

0.0

11/20/09 2,395,624.7 74.6 1,840.0 0.0 0 0.00 0.000

11/20/09 2,372,935.2 74.5 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F 0.0 F

0.0

11/23/09 2,485,179.2 67.7 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,348,924.0 67.8 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,333,722.2 68.0 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,534,674.4 68.3 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,753,038.5 67.9 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,680,417.1 67.4 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,651,541.9 66.8 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,726,521.5 66.4 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,707,223.6 66.5 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,577,573.0 66.6 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,377,037.8 66.2 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,376,351.6 66.0 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,432,635.7 65.6 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,697,134.6 65.2 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,792,590.9 64.9 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,778,770.4 64.8 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,826,950.7 64.6 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 3,899,727.8 64.4 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,784,345.6 64.3 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,757,888.2 64.3 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,744,490.8 64.7 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,619,066.2 64.7 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,513,591.1 64.7 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,496,898.2 64.7 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,474,493.6 64.8 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,485,558.6 64.9 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,505,002.9 65.0 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,731,900.9 65.4 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,754,132.7 65.5 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,715,852.1 65.5 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,741,975.7 65.7 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,678,159.3 65.8 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,661,256.6 65.6 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,660,866.6 65.4 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,622,978.1 65.1 1,840.0 0.0 0 0.00 0.000

0.0

11/22/09 2,772,714.9 65.0 1,840.0 0.0 0 0.00 0.000

11/22/09 2,808,034.5 65.2 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F 0.0 F

0.0

11/25/09 2,476,701.7 72.2 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,519,014.1 72.1 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,677,796.2 72.0 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,715,991.4 71.8 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,748,999.8 71.9 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,696,992.6 71.8 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 3,855,695.5 71.4 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,809,481.3 71.0 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,762,817.2 70.5 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,676,677.4 70.3 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,762,859.6 69.8 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,734,827.0 69.5 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,567,359.6 68.8 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,521,064.0 68.1 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,458,773.7 67.5 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,409,932.3 66.9 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,556,621.9 66.4 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,565,321.7 66.3 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,548,990.5 66.3 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,550,954.0 66.4 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,552,282.8 66.3 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,538,186.4 66.1 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,524,556.5 66.2 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,539,237.5 66.5 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,578,921.3 66.9 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,484,448.8 67.5 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,685,262.6 67.8 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,766,521.4 67.9 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,802,270.4 67.8 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,796,783.9 67.8 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 3,894,100.2 67.8 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,786,204.5 67.4 1,840.0 0.0 0 0.00 0.000

0.0

11/24/09 2,810,266.8 67.5 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,672,679.5 67.4 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,482,287.0 67.4 1,840.0 0.0 0 0.00 0.000

0.0

11/23/09 2,551,670.0 67.6 1,840.0 0.0 0 0.00 0.000

11/23/09 2,594,808.1 67.7 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F 0.0 F

0.0

11/26/09 2,854,847.4 67.3 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,881,030.9 67.7 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,708,968.4 68.1 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,631,600.2 68.4 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,624,794.5 68.7 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,650,465.9 69.1 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,744,820.8 69.2 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,766,679.7 69.3 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,754,484.2 69.2 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,768,157.4 69.2 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,646,744.2 69.3 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,581,884.4 69.5 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,634,410.5 69.9 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,721,138.8 70.3 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,744,458.8 70.5 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,735,744.3 70.7 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,795,733.6 71.1 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,769,211.6 71.9 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,791,706.7 72.2 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 3,885,067.7 72.4 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,814,823.3 72.5 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,594,690.1 72.6 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,710,719.9 72.6 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,756,868.4 72.7 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,650,422.9 72.7 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,380,046.4 72.8 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,361,179.0 72.9 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,366,782.1 72.9 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,321,494.2 73.0 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,293,336.0 73.1 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,410,920.3 73.0 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,555,106.0 72.9 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,572,997.7 72.9 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,497,689.9 72.7 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,537,096.5 72.6 1,840.0 0.0 0 0.00 0.000

0.0

11/25/09 2,496,360.1 72.4 1,840.0 0.0 0 0.00 0.000

11/25/09 2,504,214.8 72.3 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F 0.0 F

0.0

11/28/09 2,607,042.4 61.1 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,635,531.2 60.1 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,794,358.5 59.4 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,883,468.9 59.4 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,869,580.5 59.5 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,918,078.8 59.1 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,934,501.9 59.2 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,958,125.3 59.4 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 3,991,109.1 59.6 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,961,868.9 59.9 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,977,768.9 60.2 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,964,152.2 60.3 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,852,977.0 60.5 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,880,580.5 60.8 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,895,064.4 61.0 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,837,483.1 61.2 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,513,276.3 61.2 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,557,553.6 61.6 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,675,772.7 62.1 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,726,433.1 62.8 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,689,871.9 63.6 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,617,615.4 64.1 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,587,614.5 64.3 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,554,011.1 64.1 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,575,071.4 64.0 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,688,870.7 63.9 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,737,270.4 64.0 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,838,236.8 64.3 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,810,718.1 64.8 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,788,529.9 65.2 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,881,478.3 65.6 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,920,798.4 66.0 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 3,942,725.5 66.3 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,892,447.1 66.5 1,840.0 0.0 0 0.00 0.000

0.0

11/27/09 2,795,910.3 66.6 1,840.0 0.0 0 0.00 0.000

0.0

11/26/09 2,905,595.9 66.9 1,840.0 0.0 0 0.00 0.000

11/26/09 2,834,500.1 67.1 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F 0.0 F

0.0

11/29/09 2,862,087.8 63.1 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,814,723.9 63.4 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,692,907.8 63.7 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,655,942.0 63.7 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,604,454.3 63.5 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,607,052.6 63.6 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,569,812.1 63.6 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,612,254.8 63.6 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,668,263.0 63.5 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,580,235.2 63.4 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,622,609.5 63.2 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,604,204.1 62.9 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,572,956.6 62.7 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,623,453.5 62.7 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,709,562.8 62.7 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,745,283.5 62.6 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,837,797.2 62.8 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,921,926.5 63.0 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,912,860.0 63.2 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,890,099.2 63.2 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,901,500.2 63.4 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 3,943,888.7 63.6 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,899,097.4 63.8 1,840.0 0.0 0 0.00 0.000

0.0

11/29/09 2,874,982.8 64.0 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,828,466.8 64.2 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,869,978.9 64.3 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,800,314.5 64.3 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,796,418.2 64.2 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,731,884.4 63.9 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,523,095.3 63.3 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,448,318.1 62.8 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,573,903.8 62.7 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,707,610.0 62.7 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,740,978.2 62.7 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,715,166.9 62.6 1,840.0 0.0 0 0.00 0.000

0.0

11/28/09 2,674,147.6 62.4 1,840.0 0.0 0 0.00 0.000

11/28/09 2,647,965.7 61.9 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F 0.0 F

0.0

12/01/09 1,017,197.5 64.5 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 1,016,356.5 64.2 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 1,034,328.7 63.6 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 1,004,085.1 62.8 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 967,599.5 62.1 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 777,755.3 61.9 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 817,161.8 62.4 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 903,011.1 62.6 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 955,882.0 62.8 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 946,933.2 63.0 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 2,659,253.0 63.1 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 950,891.0 63.2 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 941,623.4 63.1 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 914,985.4 62.8 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 851,276.2 62.5 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 850,620.3 62.3 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 846,995.2 62.1 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 855,553.2 62.2 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 858,518.1 62.5 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 868,340.3 63.4 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,475,022.9 65.3 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,744,422.6 65.4 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,590,728.2 64.7 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,542,677.4 64.1 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,649,050.9 63.3 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,642,420.3 62.8 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,636,087.6 62.3 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,684,798.5 61.9 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,567,022.0 61.9 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,768,875.8 61.9 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,928,599.9 62.1 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,928,121.9 62.1 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,960,177.0 62.1 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,911,879.1 62.3 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 3,934,408.0 62.5 1,840.0 0.0 0 0.00 0.000

0.0

11/30/09 2,866,147.3 62.7 1,840.0 0.0 0 0.00 0.000

11/30/09 2,909,895.7 63.0 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F 0.0 F

0.0

12/03/09 1,230,975.6 63.8 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,227,229.0 63.7 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,239,420.6 63.5 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,172,360.9 63.3 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,116,300.9 63.1 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,059,399.6 63.3 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,041,469.0 63.7 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,076,470.4 63.9 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,074,618.4 63.7 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,073,509.8 63.6 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,103,232.6 63.8 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,103,530.0 64.0 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,097,272.0 63.9 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,078,366.7 63.7 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,049,395.1 63.4 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,076,991.6 62.9 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,080,827.3 62.6 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,056,302.0 62.6 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,030,047.4 62.6 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,050,936.0 62.8 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,105,335.6 62.9 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,140,074.0 62.9 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,187,144.8 62.8 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 2,824,883.7 62.5 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,223,863.1 62.3 1,840.0 0.0 0 0.00 0.000

0.0

12/02/09 1,131,146.1 62.1 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 1,121,331.3 62.1 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 1,040,963.1 62.1 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 1,036,041.4 62.6 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 1,015,053.2 63.2 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 1,018,209.6 63.5 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 1,023,446.2 63.6 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 1,032,593.0 63.6 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 1,045,069.8 63.8 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 1,067,314.9 64.1 1,840.0 0.0 0 0.00 0.000

0.0

12/01/09 1,013,716.9 64.5 1,840.0 0.0 0 0.00 0.000

12/01/09 1,024,205.1 64.6 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F 0.0 F

0.0

12/04/09 1,231,770.6 55.8 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,202,004.6 55.9 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,189,133.4 56.1 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,185,551.8 56.4 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,187,272.3 56.3 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,190,670.3 56.3 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,222,901.8 56.5 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,277,649.1 57.1 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,264,678.2 57.6 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,293,868.6 58.0 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,331,185.8 58.2 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,330,105.4 58.2 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 2,901,802.2 58.4 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,329,395.3 58.6 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,270,093.1 58.8 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,285,651.3 59.2 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,254,071.8 59.5 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,174,897.4 59.8 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,156,818.7 60.1 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,147,248.6 60.4 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,127,621.4 60.8 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,125,672.8 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,133,012.1 61.5 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,155,150.5 61.8 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,133,296.4 62.0 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,104,542.8 62.2 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,118,997.1 62.4 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,127,489.8 62.6 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,120,340.5 62.7 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,158,900.2 62.9 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,142,145.9 63.0 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,167,040.0 63.4 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,246,389.3 63.7 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,264,694.2 63.7 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,293,677.1 63.8 1,840.0 0.0 0 0.00 0.000

0.0

12/03/09 1,267,347.9 63.7 1,840.0 0.0 0 0.00 0.000

12/03/09 2,859,855.3 63.6 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F 0.0 F

0.0

12/06/09 987,957.5 57.4 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 2,674,226.4 56.9 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 954,758.2 56.6 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 951,467.5 56.3 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 953,321.7 56.0 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 889,911.6 55.7 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 876,175.2 55.6 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 863,147.6 55.4 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 887,335.7 55.2 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 869,198.9 55.1 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 876,273.9 55.0 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 914,643.0 55.1 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 942,588.4 54.7 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 880,739.6 54.1 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 893,883.6 53.5 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 831,449.6 52.6 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 868,778.9 51.7 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 890,425.3 51.0 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 893,929.6 50.5 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 884,057.8 50.1 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 931,971.8 50.1 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 987,989.4 50.1 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 1,020,756.0 49.9 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 1,016,095.6 49.7 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 1,025,216.5 49.7 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 2,737,415.6 50.5 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 1,247,553.0 51.4 1,840.0 0.0 0 0.00 0.000

0.0

12/05/09 1,234,272.9 52.2 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,218,749.9 52.6 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,233,689.0 53.0 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,223,297.3 53.3 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,218,790.6 53.5 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,218,777.5 53.8 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,220,284.7 54.2 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,217,464.0 54.6 1,840.0 0.0 0 0.00 0.000

0.0

12/04/09 1,224,248.6 55.1 1,840.0 0.0 0 0.00 0.000

12/04/09 1,229,435.7 55.4 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F 0.0 F

0.0

12/07/09 932,482.9 61.6 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 939,076.5 61.7 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 953,609.1 61.7 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 944,615.9 61.6 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 947,974.5 61.6 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 943,658.2 61.5 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 947,501.9 61.3 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 936,307.8 61.2 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 938,140.9 61.3 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 931,213.7 61.3 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 932,768.9 61.4 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 975,661.2 61.4 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 984,520.7 61.4 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 987,561.2 61.6 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 2,691,029.6 61.7 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 983,906.9 61.8 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 958,430.5 61.8 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 945,906.2 61.6 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 922,396.8 61.5 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 904,606.7 61.4 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 902,706.5 61.5 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 893,878.2 61.7 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 864,207.0 61.7 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 838,621.6 61.6 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 852,758.0 61.5 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 893,689.9 61.3 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 896,031.9 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 871,806.2 61.0 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 858,120.7 60.8 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 794,514.3 60.3 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 831,254.5 59.6 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 868,705.3 59.1 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 904,510.9 58.8 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 915,617.8 58.6 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 924,362.0 58.4 1,840.0 0.0 0 0.00 0.000

0.0

12/06/09 951,571.1 58.3 1,840.0 0.0 0 0.00 0.000

12/06/09 972,778.8 57.9 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F 0.0 F

0.0

12/09/09 871,026.4 59.3 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 880,734.1 59.0 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 893,801.6 58.8 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 2,644,208.5 58.5 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 912,483.0 58.2 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 871,672.5 58.0 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 903,748.9 58.4 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 919,504.1 58.7 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 879,690.7 58.8 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 834,549.9 59.1 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 785,182.1 59.4 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 806,158.5 60.1 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 841,056.4 60.8 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 892,080.5 61.5 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 916,776.8 61.7 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 936,531.6 62.0 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 912,290.7 61.7 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 862,652.1 61.5 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 869,614.7 61.5 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 897,888.8 61.5 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 942,787.3 61.3 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 915,623.2 61.0 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 971,168.0 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 1,007,244.4 60.9 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 967,239.8 60.6 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 978,631.0 60.7 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 995,181.3 60.8 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 2,705,039.3 60.9 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 1,006,415.0 60.9 1,840.0 0.0 0 0.00 0.000

0.0

12/08/09 982,123.3 60.9 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 988,784.8 61.0 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 953,352.4 60.9 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 915,402.6 60.9 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 920,368.6 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 921,719.9 61.2 1,840.0 0.0 0 0.00 0.000

0.0

12/07/09 930,670.8 61.3 1,840.0 0.0 0 0.00 0.000

12/07/09 930,150.2 61.4 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F 0.0 F

0.0

12/10/09 1,197,735.6 55.7 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,197,167.4 56.2 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,204,346.3 56.9 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,229,952.2 57.4 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,223,155.8 57.5 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,204,670.4 57.3 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,213,766.9 57.2 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,249,045.0 57.0 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,232,112.8 56.8 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,224,311.9 57.1 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,222,558.3 57.7 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,228,134.0 58.2 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,217,713.1 58.5 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,229,433.7 59.0 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,250,293.5 59.5 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,238,486.5 59.7 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 2,834,609.0 60.1 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,217,763.0 60.6 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,198,367.4 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 1,156,614.5 61.6 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 1,102,729.5 62.2 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 1,063,975.2 62.8 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 1,003,130.1 63.1 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 986,057.4 63.3 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 938,695.2 63.2 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 926,614.9 63.2 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 897,355.1 63.2 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 889,587.8 63.0 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 911,999.7 62.5 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 885,370.0 61.9 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 856,053.0 61.5 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 846,995.3 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 821,582.5 60.6 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 812,738.1 60.3 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 820,160.9 60.1 1,840.0 0.0 0 0.00 0.000

0.0

12/09/09 824,914.4 59.9 1,840.0 0.0 0 0.00 0.000

12/09/09 868,798.3 59.7 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F 0.0 F

0.0

12/12/09 1,151,410.2 58.4 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 1,187,679.3 58.3 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 1,176,608.8 58.2 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 1,194,883.8 58.0 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 1,196,174.8 57.8 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 2,841,943.6 57.7 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 1,232,021.4 57.3 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 1,246,275.1 57.2 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,271,945.2 57.0 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,234,820.2 56.6 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,218,524.8 56.7 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,220,927.9 57.0 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,223,863.6 57.4 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,209,043.3 57.6 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,206,329.5 57.7 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,199,288.7 57.9 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,180,990.6 58.0 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,141,175.8 57.9 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,088,870.7 57.4 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,118,738.1 56.9 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,165,386.3 56.2 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,222,934.9 55.4 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,240,918.9 54.6 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,243,305.7 54.1 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,233,289.9 54.2 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,255,458.8 54.8 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,307,013.8 55.2 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,288,892.2 55.3 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,330,021.2 55.4 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 2,906,603.5 55.0 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,254,544.4 54.7 1,840.0 0.0 0 0.00 0.000

0.0

12/11/09 1,235,631.5 54.8 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,233,054.4 55.0 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,229,024.8 55.1 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,223,709.0 55.1 1,840.0 0.0 0 0.00 0.000

0.0

12/10/09 1,208,043.6 55.2 1,840.0 0.0 0 0.00 0.000

12/10/09 1,197,451.7 55.4 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F 0.0 F

0.0

12/13/09 948,188.3 69.1 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 937,704.9 69.0 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 956,324.9 68.9 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 934,377.7 68.9 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 941,107.3 68.9 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 946,341.8 68.7 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 938,616.2 68.6 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 933,009.1 68.7 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 937,388.1 68.8 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 932,406.0 68.8 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 936,938.8 68.7 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 927,759.0 68.5 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 921,835.7 68.5 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 935,156.7 68.3 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 966,809.1 68.1 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 990,489.3 67.8 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 1,007,387.8 67.4 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 1,008,411.0 66.9 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 2,695,403.7 66.5 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 1,002,598.5 65.9 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 977,859.6 65.4 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 948,877.9 65.0 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 927,176.0 64.7 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 884,965.8 64.3 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 871,968.0 63.8 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 851,429.0 63.7 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 855,618.6 63.6 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 854,315.4 63.5 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 882,249.4 63.5 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 883,784.5 63.4 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 922,651.1 63.0 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 923,612.7 62.5 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 921,174.0 61.8 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 927,678.6 60.9 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 967,551.3 59.8 1,840.0 0.0 0 0.00 0.000

0.0

12/12/09 1,021,471.4 58.9 1,840.0 0.0 0 0.00 0.000

12/12/09 1,100,876.0 58.4 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F FM

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F 0.0 F

0.0

12/15/09 1,221,245.6 63.5 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,233,955.7 64.0 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,230,217.9 65.0 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,210,513.3 65.8 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,171,578.5 66.6 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,142,758.6 67.1 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,131,602.1 67.3 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 2,769,715.7 67.5 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,147,723.6 68.0 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,147,729.1 68.0 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 1,095,558.9 68.0 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 1,033,417.0 68.1 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 1,011,633.5 68.3 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 993,195.4 68.4 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 980,991.0 68.5 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 988,985.1 68.6 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 982,099.8 68.8 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 986,400.1 69.2 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 979,140.1 69.6 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 988,704.3 70.0 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 972,429.5 70.3 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 933,132.8 70.5 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 869,412.3 70.4 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 862,369.3 70.3 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 888,270.7 70.4 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 897,256.5 70.5 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 881,373.7 70.8 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 951,348.9 71.2 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 973,469.0 70.8 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 940,114.7 70.7 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 972,257.1 70.6 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 2,675,620.3 70.1 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 961,547.4 69.7 1,840.0 0.0 0 0.00 0.000

0.0

12/14/09 984,854.5 69.6 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 968,014.3 69.2 1,840.0 0.0 0 0.00 0.000

0.0

12/13/09 953,130.6 69.1 1,840.0 0.0 0 0.00 0.000

12/13/09 940,981.8 69.1 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F FM

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F 0.0 F

0.0

12/16/09 1,155,400.3 58.8 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,172,286.4 58.7 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,181,052.4 58.6 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,168,109.4 58.6 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,168,713.9 58.5 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,175,866.6 58.6 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,175,325.8 58.5 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,178,304.3 58.3 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,170,395.0 58.0 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,156,491.8 57.5 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,207,055.8 57.1 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,233,774.1 56.7 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,257,640.9 56.5 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,258,685.3 56.3 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,256,679.4 56.3 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,253,226.3 56.4 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,273,073.9 56.9 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,354,882.9 57.2 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,337,669.4 57.1 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,300,106.7 57.2 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 2,900,293.2 57.5 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,320,806.5 57.5 1,840.0 0.0 0 0.00 0.000

0.0

12/16/09 1,283,992.0 57.4 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,257,474.5 57.5 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,255,173.4 57.8 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,231,831.5 58.0 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,228,768.3 58.5 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,236,255.6 59.0 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,233,992.1 59.5 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,237,435.6 60.0 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,237,179.9 60.4 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,247,482.0 60.9 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,227,014.6 61.4 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,202,202.6 61.8 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,191,883.6 62.5 1,840.0 0.0 0 0.00 0.000

0.0

12/15/09 1,200,801.3 63.1 1,840.0 0.0 0 0.00 0.000

12/15/09 1,227,041.5 63.4 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F 0.0 F

0.0

12/18/09 913,715.2 65.6 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 915,842.5 65.4 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 933,210.9 65.4 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 927,158.9 65.5 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 915,739.1 65.4 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 955,471.6 65.6 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 1,003,723.1 65.5 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 1,006,950.4 65.2 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 994,516.0 65.0 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 2,680,937.3 64.6 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 930,070.4 64.3 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 920,158.4 64.1 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 894,940.1 63.8 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 889,825.4 63.5 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 890,724.1 63.4 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 897,117.9 63.2 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 907,814.2 63.2 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 916,905.8 63.2 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 921,461.7 63.3 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 937,637.1 63.3 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 935,990.3 63.1 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 917,499.6 62.9 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 918,670.8 62.6 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 934,076.9 62.3 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 944,685.5 62.2 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 943,337.8 62.1 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 948,954.1 61.8 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 926,922.5 61.4 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 941,395.1 61.3 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 1,071,750.4 61.4 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 1,167,082.0 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 1,111,382.4 60.4 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 1,111,635.4 59.9 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 2,808,206.1 59.7 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 1,206,393.0 59.5 1,840.0 0.0 0 0.00 0.000

0.0

12/17/09 1,181,584.3 59.2 1,840.0 0.0 0 0.00 0.000

12/16/09 1,144,036.5 59.0 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F 0.0 F

0.0

12/20/09 1,089,628.3 65.2 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 1,090,756.2 65.4 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 1,032,999.6 65.5 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 1,007,469.2 65.7 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 997,074.6 66.0 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 987,352.1 66.2 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 979,459.3 66.4 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 968,700.8 66.6 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 964,898.0 66.7 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 968,549.4 66.8 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 948,809.3 67.1 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 926,116.0 67.2 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 929,035.9 67.2 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 920,213.5 67.4 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 926,935.8 67.5 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 930,162.0 67.6 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 966,460.7 67.8 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 949,321.9 67.8 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 954,694.6 67.9 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 1,009,161.8 68.2 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 1,039,347.3 68.3 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 1,041,083.6 68.2 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 2,721,854.8 68.1 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 999,750.2 68.0 1,840.0 0.0 0 0.00 0.000

0.0

12/19/09 1,014,641.8 67.9 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 1,005,557.6 67.9 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 976,809.0 67.6 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 951,764.4 67.5 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 947,320.1 67.5 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 957,651.9 67.6 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 957,659.8 67.5 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 953,892.7 67.2 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 940,374.8 66.9 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 942,132.4 66.5 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 942,753.2 66.3 1,840.0 0.0 0 0.00 0.000

0.0

12/18/09 942,994.2 66.1 1,840.0 0.0 0 0.00 0.000

12/18/09 931,018.1 65.9 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F 0.0 F

0.0

12/21/09 944,168.6 61.9 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 921,796.6 61.6 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 925,542.0 61.3 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 937,094.3 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 967,676.8 61.0 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 965,285.2 60.9 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 976,465.9 60.9 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 1,007,431.6 61.2 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 1,030,306.0 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 1,020,009.8 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 1,023,347.5 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 2,718,687.0 61.3 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 1,053,257.1 61.3 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 1,047,222.3 61.3 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,053,437.8 61.5 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,049,480.0 61.6 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,035,674.5 61.7 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,034,782.2 61.7 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,030,356.9 61.9 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,027,663.6 62.0 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,015,481.5 62.2 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,011,818.5 62.4 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,013,188.2 62.5 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 993,295.9 62.3 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 966,296.5 62.0 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,041,494.2 62.1 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,058,408.5 62.4 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,058,207.0 62.7 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,053,713.0 63.0 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,048,953.4 63.2 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,087,134.8 63.5 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,129,021.1 63.9 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,145,673.9 64.2 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,148,469.6 64.5 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 1,138,396.7 64.6 1,840.0 0.0 0 0.00 0.000

0.0

12/20/09 2,759,819.7 64.8 1,840.0 0.0 0 0.00 0.000

12/20/09 1,123,071.6 65.0 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F 0.0 F

0.0

12/23/09 2,571,112.6 58.8 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 806,925.9 58.9 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 802,121.3 59.0 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 795,407.6 59.0 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 770,780.2 58.9 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 758,055.1 59.2 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 751,705.6 59.4 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 747,579.3 59.7 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 748,573.7 60.0 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 745,537.3 60.2 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 746,651.6 60.4 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 753,168.0 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 843,283.9 62.6 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 1,005,529.0 62.7 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 909,537.0 61.9 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 909,758.8 61.8 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 916,713.7 61.7 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 914,373.1 61.9 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 921,163.1 62.4 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 969,030.8 62.7 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 1,042,577.1 63.0 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 1,027,529.9 63.0 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 1,024,121.9 63.0 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 1,016,902.0 62.8 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 2,715,955.8 62.8 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 1,033,024.7 62.7 1,840.0 0.0 0 0.00 0.000

0.0

12/22/09 1,029,265.2 62.5 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 978,408.2 62.3 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 966,393.3 62.3 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 949,724.0 62.3 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 944,615.6 62.3 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 952,955.0 62.4 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 946,633.4 62.4 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 928,036.2 62.3 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 941,187.5 62.4 1,840.0 0.0 0 0.00 0.000

0.0

12/21/09 945,824.6 62.2 1,840.0 0.0 0 0.00 0.000

12/21/09 939,430.6 62.1 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F 0.0 F

0.0

12/24/09 712,748.0 58.8 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 698,742.4 58.7 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 727,810.1 58.6 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 708,479.2 58.1 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 690,407.5 57.7 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 688,005.7 57.4 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 700,989.9 57.4 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 732,283.1 57.4 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 737,322.7 57.2 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 738,939.3 57.0 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 755,594.7 57.0 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 770,185.5 57.0 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 765,322.1 57.0 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 2,537,879.1 57.1 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 776,177.3 57.2 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 760,523.5 57.3 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 762,799.0 57.3 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 785,173.6 57.1 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 759,567.8 56.6 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 765,898.7 56.4 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 769,374.0 56.2 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 761,655.5 56.2 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 761,819.9 56.4 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 773,661.6 56.6 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 773,749.7 56.7 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 844,749.8 58.5 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 907,635.1 59.2 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 906,126.8 58.8 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 909,083.6 58.1 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 829,347.2 56.7 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 776,342.2 56.6 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 768,148.0 56.8 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 774,287.9 57.3 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 801,443.8 57.9 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 814,835.7 58.2 1,840.0 0.0 0 0.00 0.000

0.0

12/23/09 802,883.1 58.5 1,840.0 0.0 0 0.00 0.000

12/23/09 812,825.0 58.7 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F 0.0 F

0.0

12/26/09 895,685.9 59.4 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 860,625.5 59.2 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 2,593,331.6 58.7 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 879,943.2 58.5 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 882,481.1 58.2 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 883,615.8 58.6 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 880,323.3 58.8 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 800,102.8 59.3 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 733,379.2 59.7 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 719,696.6 60.0 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 686,265.2 59.8 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 679,098.6 59.5 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 668,987.8 59.0 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 683,552.4 58.9 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 678,315.9 58.6 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 674,034.9 58.2 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 668,557.3 57.6 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 657,610.2 57.1 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 652,746.2 56.9 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 668,643.8 56.9 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 696,574.9 56.7 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 678,225.9 56.5 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 673,409.8 56.8 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 669,562.7 57.2 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 681,452.3 57.6 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 670,490.0 57.7 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 2,480,068.1 57.8 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 672,339.4 58.0 1,840.0 0.0 0 0.00 0.000

0.0

12/25/09 677,454.7 58.0 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 686,761.6 58.0 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 688,130.0 57.9 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 674,710.0 57.9 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 670,444.3 58.1 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 693,098.6 58.4 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 734,006.9 58.8 1,840.0 0.0 0 0.00 0.000

0.0

12/24/09 738,918.2 59.0 1,840.0 0.0 0 0.00 0.000

12/24/09 702,364.3 58.9 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F 0.0 F

0.0

12/27/09 940,538.8 60.5 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 968,172.3 60.5 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 961,536.6 60.4 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 955,017.0 60.3 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 937,636.5 60.1 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 931,208.9 59.8 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 933,362.8 59.5 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 949,170.1 59.2 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 974,787.8 59.2 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 1,015,457.7 59.2 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 1,040,692.8 59.3 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 1,047,238.7 59.5 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 1,047,768.4 59.8 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 1,053,915.8 60.0 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 1,057,137.1 60.2 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 2,703,876.3 60.3 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 1,009,698.4 60.3 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 980,684.5 60.4 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 957,533.6 60.6 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 949,948.5 60.6 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 931,897.2 60.7 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 915,934.8 60.7 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 890,198.5 60.7 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 881,805.6 60.7 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 844,910.2 60.6 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 823,286.3 60.4 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 825,994.6 60.3 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 838,165.2 60.1 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 813,478.7 59.7 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 812,276.5 59.5 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 797,923.0 59.3 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 818,288.0 59.1 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 864,387.5 59.0 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 880,958.8 59.0 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 879,403.3 58.9 1,840.0 0.0 0 0.00 0.000

0.0

12/26/09 905,266.2 59.0 1,840.0 0.0 0 0.00 0.000

12/26/09 919,420.5 59.4 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F 0.0 F

0.0

12/29/09 1,031,714.8 54.9 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 1,039,681.7 55.4 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 1,033,702.2 55.8 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 1,031,259.8 56.4 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 2,707,642.2 56.9 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 1,022,192.9 57.4 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 1,020,816.1 57.9 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 1,015,432.0 58.5 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 1,007,997.7 59.2 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 996,236.9 59.7 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 982,241.3 60.3 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 950,636.6 60.8 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 928,480.3 61.3 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 913,369.2 61.7 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 891,619.3 62.2 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 865,082.1 62.6 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 862,024.1 63.0 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 808,276.7 63.2 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 769,505.8 63.0 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 781,518.7 62.9 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 775,107.7 62.6 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 767,800.7 62.0 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 759,974.0 61.7 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 761,816.4 61.6 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 780,418.6 61.8 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 819,045.8 61.9 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 818,586.0 61.6 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 845,869.0 61.3 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 2,605,997.6 61.0 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 868,858.3 60.8 1,840.0 0.0 0 0.00 0.000

0.0

12/28/09 869,193.3 60.8 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 907,085.7 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 910,921.1 61.1 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 902,705.2 61.0 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 893,765.8 60.8 1,840.0 0.0 0 0.00 0.000

0.0

12/27/09 916,867.9 60.7 1,840.0 0.0 0 0.00 0.000

12/27/09 930,657.8 60.6 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F 0.0 F

0.0

12/30/09 756,375.9 57.7 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 752,464.0 57.6 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 751,733.6 57.6 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 755,196.5 57.5 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 751,748.7 57.2 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 751,155.9 56.8 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 753,005.9 56.4 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 766,503.3 56.0 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 779,826.2 55.6 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 797,491.1 55.2 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 810,672.1 54.8 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 820,786.1 54.5 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 832,035.6 54.0 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 866,483.0 53.7 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 900,242.2 53.7 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 946,386.8 53.9 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 987,347.5 54.0 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 2,695,782.7 54.1 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 1,013,307.0 54.2 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 1,010,171.7 54.5 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 1,005,370.5 54.8 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 1,000,185.8 55.2 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 994,253.5 55.6 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 988,936.1 56.3 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 970,041.6 56.8 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 924,237.7 57.0 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 887,802.2 56.9 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 875,701.7 57.1 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 881,409.1 57.2 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 885,374.8 57.1 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 865,747.8 57.0 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 871,989.0 56.8 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 886,087.6 56.1 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 927,734.0 55.1 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 978,508.4 54.3 1,840.0 0.0 0 0.00 0.000

0.0

12/29/09 1,020,442.3 54.1 1,840.0 0.0 0 0.00 0.000

12/29/09 1,033,492.6 54.3 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

00:00 F F F F F F F F F

01:00 F F F F F F F F F

02:00 FC F F F F F F F F

03:00 F F F F F F F F F

04:00 F F F F F F F F F

05:00 FC F F F F F F F F

06:00 F F F F F F F F F

07:00 F F F F F F F F F

08:00 F F F F F F F F F

09:00 F F F F F F F F F

10:00 F F F F F F F F F

11:00 F F F F F F F F F

12:00 F F F F F F F F F

13:00 F F F F F F F F F

14:00 F F F F F F F F F

15:00 F F F F F F F F F

16:00 F F F F F F F F F

17:00 F F F F F F F F F

18:00 F F F F F F F F F

19:00 F F F F F F F F F

20:00 F F F F F F F F F

21:00 F F F F F F F F F

22:00 F F F F F F F F F

23:00 F F F F F F F F F

Included Data 5639 5639 5639 5639 5639 5639

Points

5639 5638 5639

51.729 6,284.4

63.984 0.577 61.3

Summation 43,967,447,707.8 1,473,384.8 10,375,760.0 2,460,852.5 220,149 337,841.00

0.000 0.000 0.0

Maximum 14,090,444.0 319.0 1,840.0 865.7 76 60.00

0.009 1.1

Minimum 1,823,867.0 75.6 1,840.0 1.0 0 1.00

0.0

Average 7,797,029.2 261.3 1,840.0 436.4 39 59.91

0.0

12/31/09 985,897.3 55.5 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 988,447.1 55.7 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 998,414.6 55.9 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 1,012,240.8 56.4 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 1,004,464.4 56.7 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 985,091.0 57.1 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 971,847.9 57.4 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 981,822.8 57.9 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 982,300.4 58.3 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 983,626.7 58.7 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 950,652.5 58.9 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 937,509.2 59.2 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 924,788.2 59.3 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 906,994.5 59.7 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 889,089.3 60.1 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 796,951.2 60.4 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 744,852.0 60.4 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 745,440.5 60.3 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 762,769.0 60.2 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 769,916.7 59.9 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 784,307.6 59.9 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 2,534,491.1 59.4 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 746,411.5 59.0 1,840.0 0.0 0 0.00 0.000

0.0

12/31/09 738,487.6 58.6 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 742,945.6 58.3 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 747,877.7 58.0 1,840.0 0.0 0 0.00 0.000

0.0

12/30/09 758,383.0 57.8 1,840.0 0.0 0 0.00 0.000

12/30/09 758,173.8 57.7 1,840.0 0.0 0 0.00 0.000
Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES

 (OZ)

HGT

 (UG/M3)

 Time Online Criteria: 1 minute(s)

Edgewater - Unit 3 

D3CPFLOW

 (SCFH)

D3DTEMP

 (DEGF)

D3FFACT

 (SCF/MBTU)

D3HIBAF

 (MMBTU/HR)

D3MEG

 (MEGAWATT)

D3TOLG

 (MINUTES)

HGLB/T

 (LB/TBTU)

Average Data

Plant: EDGEWATER

Interval: 1 Hour

Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source

 Parameter (Unit)

Total number of 

Data Points

8760 8760 8760 8760 8760 8760 8760 8760 8760