Facility DEC ID: 1282000553

 DEC Permit Conditions

 Renewal 2/Mod 1/FINAL Page 1

 PERMIT

 Under the Environmental Conservation Law (ECL)

 IDENTIFICATION INFORMATION

Permit Type: Air Title V Facility

Permit ID: 1-2820-00553/00025

 Mod 0 Effective Date: 02/24/2011 Expiration Date: 02/23/2016

 Mod 1 Effective Date: 03/27/2012 Expiration Date: 02/23/2016

Permit Issued To:NATIONAL GRID GENERATION LLC

 175 E OLD COUNTRY RD

 HICKSVILLE, NY 11801

 NATIONAL GRID CORPORATE SERVICES LLC

 175 E OLD COUNTRY RD

 HICKSVILLE, NY 11801

Contact: CHRISTOPHER CORRADO

 NATIONAL GRID GENERATION LLC

 175 E OLD COUNTRY ROAD

 HICKSVILLE, NY 11801

 (516) 545-2556

Facility: EF BARRETT POWER STATION

 1 MCCARTHY RD

 ISLAND PARK, NY 11558

Description:

Application for modification of Air Title V Facility for an existing electric generating plant

consisting of two (2) 185 MWe turbine/generator boiler sets operating on natural gas, #1, #2 or

#6 fuel oils. The combustion turbines operate on either natural gas, #1, or #2 fuel oils. In

addition, an industrial steam boiler is maintained on site for building heat. In addition to pipeline

natural gas, #1, #2 and #6 fuel oil in the steam turbine boilers burn waste oil generated on and

off site for energy recovery, and incinerate citrosolv, a boiler cleaning solution, following boiler

chemical cleaning. There are numerous tanks used for storing distillate, lubrication and/or

electrical cable oils at this facility. A complete list of tanks is included in the documentation

section of this application. Twelve combustion turbine-generators ( four of which contain two

engines per generator ) are maintained on site to meet system load demands. The following

regulations are added to this permit renewal: Parts 242, 243,244, 245. These regulations deal

with CO2, NOx and SO2 Budget Program.

This purpose of this modification is to incorporate the Best Available Retrofit Technology Rule,

6NYCRR Part 249. New emission limits for NOx, Oil Sulfur Content, and PM are included in

this permit modification.
 

Facility DEC ID: 1282000553

 DEC Permit Conditions

 Renewal 2/Mod 1/FINAL Page 2

By acceptance of this permit, the permittee agrees that the permit is contingent upon strict

compliance with the ECL, all applicable regulations, the General Conditions specified and any

Special Conditions included as part of this permit.

Permit Administrator: ROGER EVANS

 NYSDEC - SUNY @ STONY BROOK

 50 CIRCLE RD

 STONY BROOK, NY 11790-3409

Authorized Signature: _________________________________ Date: ___ / ___ / _____
 

Facility DEC ID: 1282000553

 DEC Permit Conditions

 Renewal 2/Mod 1/FINAL Page 3

 Notification of Other State Permittee Obligations

Item A: Permittee Accepts Legal Responsibility and Agrees to Indemnification

 The permittee expressly agrees to indemnify and hold harmless the Department of

 Environmental Conservation of the State of New York, its representatives,

 employees and agents ("DEC") for all claims, suits, actions, and damages, to the

 extent attributable to the permittee's acts or omissions in connection with the

 compliance permittee's undertaking of activities in connection with, or operation

 and maintenance of, the facility or facilities authorized by the permit whether in

 compliance or not in any compliance with the terms and conditions of the permit.

 This indemnification does not extend to any claims, suits, actions, or damages to

 the extent attributable to DEC's own negligent or intentional acts or omissions, or

 to any claims, suits, or actions naming the DEC and arising under article 78 of the 

 New York Civil Practice Laws and Rules or any citizen suit or civil rights

 provision under federal or state laws.

Item B: Permittee's Contractors to Comply with Permit

 The permittee is responsible for informing its independent contractors, employees,

 agents and assigns of their responsibility to comply with this permit, including all

 special conditions while acting as the permittee's agent with respect to the

 permitted activities, and such persons shall be subject to the same sanctions for

 violations of the Environmental Conservation Law as those prescribed for the

 permittee.

Item C: Permittee Responsible for Obtaining Other Required Permits

 The permittee is responsible for obtaining any other permits, approvals, lands, 

 easements and rights-of-way that may be required to carry out the activities that

 are authorized by this permit.

Item D: No Right to Trespass or Interfere with Riparian Rights

 This permit does not convey to the permittee any right to trespass upon the lands

 or interfere with the riparian rights of others in order to perform the permitted 

 work nor does it authorize the impairment of any rights, title, or interest in real or

 personal property held or vested in a person not a party to the permit.
 

Facility DEC ID: 1282000553

 DEC Permit Conditions

 Renewal 2/Mod 1/FINAL Page 4

 LIST OF CONDITIONS

 

 DEC GENERAL CONDITIONS

 General Provisions

 Facility Inspection by the Department

 Relationship of this Permit to Other Department Orders and

 Determinations

 Applications for permit renewals, modifications and transfers

 Permit modifications, suspensions or revocations by the Department

 Permit modifications, suspensions or revocations by the Department

 Facility Level

 Submission of application for permit modification or renewal -

 REGION 1 HEADQUARTERS
 

Facility DEC ID: 1282000553

 DEC Permit Conditions

 Renewal 2/Mod 1/FINAL Page 5

 DEC GENERAL CONDITIONS

 **** General Provisions  

 For the purpose of your Title V permit, the following section contains

 state-only enforceable terms and conditions.

 GENERAL CONDITIONS - Apply to ALL Authorized Permits.

Condition 1: Facility Inspection by the Department

 Applicable State Requirement: ECL 19-0305

Item 1.1:

The permitted site or facility, including relevant records, is subject to inspection at reasonable

hours and intervals by an authorized representative of the Department of Environmental

Conservation (the Department) to determine whether the permittee is complying with this permit

and the ECL. Such representative may order the work suspended pursuant to ECL 71-0301 and

SAPA 401(3).

Item 1.2:

The permittee shall provide a person to accompany the Department's representative during an

inspection to the permit area when requested by the Department.

Item 1.3:

A copy of this permit, including all referenced maps, drawings and special conditions, must be

available for inspection by the Department at all times at the project site or facility. Failure to

produce a copy of the permit upon request by a Department representative is a violation of this

permit.

Condition 2: Relationship of this Permit to Other Department Orders and Determinations

 Applicable State Requirement: ECL 3-0301 (2) (m)

Item 2.1:

Unless expressly provided for by the Department, issuance of this permit does not modify,

supersede or rescind any order or determination previously issued by the Department or any of

the terms, conditions or requirements contained in such order or determination.

Condition 3: Applications for permit renewals, modifications and transfers

 Applicable State Requirement: 6 NYCRR 621.11

Item 3.1:

The permittee must submit a separate written application to the Department for renewal,

modification or transfer of this permit. Such application must include any forms or supplemental

information the Department requires. Any renewal, modification or transfer granted by the

Department must be in writing.

Item 3.2:

The permittee must submit a renewal application at least 180 days before expiration of permits

for Title V Facility Permits, or at least 30 days before expiration of permits for State Facility

Permits. 

Item 3.3:

Permits are transferrable with the approval of the department unless specifically prohibited by

the statute, regulation or another permit condition. Applications for permit transfer should be

submitted prior to actual transfer of ownership.
 

Facility DEC ID: 1282000553

 DEC Permit Conditions

 Renewal 2/Mod 1/FINAL Page 6

Condition 1-1: Permit modifications, suspensions or revocations by the

Department

 Applicable State Requirement: 6 NYCRR 621.13

Item 1-1.1:

The Department reserves the right to exercise all available authority to modify, suspend, or

revoke this permit in accordance with 6NYCRR Part 621. The grounds for modification,

suspension or revocation include:

a) materially false or inaccurate statements in the permit application or supporting papers;

b) failure by the permittee to comply with any terms or conditions of the permit;

c) exceeding the scope of the project as described in the permit application;

d) newly discovered material information or a material change in environmental conditions,

relevant technology or applicable law or regulations since the issuance of the existing permit;

e) noncompliance with previously issued permit conditions, orders of the commissioner, any

provisions of the Environmental Conservation Law or regulations of the Department related to

the permitted activity.

Condition 4: Permit modifications, suspensions or revocations by the Department

 Applicable State Requirement: 6 NYCRR 621.13

Item 4.1:

The Department reserves the right to modify, suspend, or revoke this permit in accordance with

6NYCRR Part 621. The grounds for modification, suspension or revocation include:

a) materially false or inaccurate statements in the permit application or supporting papers;

b) failure by the permittee to comply with any terms or conditions of the permit;

c) exceeding the scope of the project as described in the permit application;

d) newly discovered material information or a material change in environmental conditions,

relevant technology or applicable law or regulations since the issuance of the existing permit;

e) noncompliance with previously issued permit conditions, orders of the commissioner, any

provisions of the Environmental Conservation Law or regulations of the Department related to

the permitted activity.

 ** ** Facility Level  

Condition 5: Submission of application for permit modification or renewal - REGION 1 

 HEADQUARTERS

 Applicable State Requirement: 6 NYCRR 621.6 (a)

Item 5.1: 

Applications for permit modification or renewal are to be submitted to:

 NYSDEC Regional Permit Administrator

 Region 1 Headquarters

 Division of Environmental Permits

 Stony Brook University

 50 Circle Road

 Stony Brook, NY 11790-3409

 (631) 444-0365
 

Facility DEC ID: 1282000553

 DEC Permit Conditions

 Renewal 2/Mod 1/FINAL Page 7
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 1 FINAL

 Permit Under the Environmental Conservation Law (ECL)

 ARTICLE 19: AIR POLLUTION CONTROL - TITLE V PERMIT

 IDENTIFICATION INFORMATION

Permit Issued To:NATIONAL GRID GENERATION LLC

 175 E OLD COUNTRY RD

 HICKSVILLE, NY 11801

 NATIONAL GRID CORPORATE SERVICES LLC

 175 E OLD COUNTRY RD

 HICKSVILLE, NY 11801

Facility: EF BARRETT POWER STATION

 1 MCCARTHY RD

 ISLAND PARK, NY 11558

Authorized Activity By Standard Industrial Classification Code:

 4911 - ELECTRIC SERVICES

Mod 0 Permit Effective Date: 02/24/2011 Permit Expiration Date: 02/23/2016

Mod 1 Permit Effective Date: 03/27/2012 Permit Expiration Date: 02/23/2016
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 2 FINAL

 LIST OF CONDITIONS

 

 FEDERALLY ENFORCEABLE CONDITIONS

 Facility Level

 1 6 NYCRR 200.6: Acceptable Ambient Air Quality

 2 6 NYCRR 201-6.5 (a) (7): Fees

 3 6 NYCRR 201-6.5 (c): Recordkeeping and reporting of compliance 

 monitoring

 4 6 NYCRR 201-6.5 (c) (2): Monitoring, Related Recordkeeping, and 

 Reporting Requirements.

 5 6 NYCRR 201-6.5 (c) (3) (ii): Compliance Certification

 6 6 NYCRR 202-2.1: Compliance Certification

 7 6 NYCRR 202-2.5: Recordkeeping requirements

 8 6 NYCRR Part 215: Open Fires Prohibited at Industrial and Commercial 

 Sites

 9 6 NYCRR 215.2: Open Fires - Prohibitions

 10 6 NYCRR 200.7: Maintenance of Equipment

 11 6 NYCRR 201-1.7: Recycling and Salvage

 12 6 NYCRR 201-1.8: Prohibition of Reintroduction of Collected 

 Contaminants to the air

 13 6 NYCRR 201-3.2 (a): Exempt Sources - Proof of Eligibility

 14 6 NYCRR 201-3.3 (a): Trivial Sources - Proof of Eligibility

 15 6 NYCRR 201-6.5 (a) (4): Standard Requirement - Provide Information

 16 6 NYCRR 201-6.5 (a) (8): General Condition - Right to Inspect

 17 6 NYCRR 201-6.5 (d) (5): Standard Requirements - Progress Reports

 18 6 NYCRR 201-6.5 (f) (6): Off Permit Changes

 19 6 NYCRR 202-1.1: Required Emissions Tests

 20 6 NYCRR 211.3: Visible Emissions Limited

 21 40 CFR Part 68: Accidental release provisions.

 22 40CFR 82, Subpart F: Recycling and Emissions Reduction

 23 6 NYCRR Subpart 201-6: Emission Unit Definition

 24 6 NYCRR 201-6.5 (e): Compliance Certification

 1-1 6 NYCRR 211.1: Air pollution prohibited

 1-2 6 NYCRR 225-1.2 (a) (2): Compliance Certification

 1-3 6 NYCRR 225-1.2 (a) (2): Compliance Certification

 1-4 6 NYCRR 225-1.2 (a) (2): Compliance Certification

 25 6 NYCRR 225-1.2 (a) (2): Compliance Certification

 26 6 NYCRR 225-1.2 (a) (2): Compliance Certification

 27 6 NYCRR 225-1.2 (a) (2): Compliance Certification

 1-5 6 NYCRR 225-2.3: Compliance Certification

 28 6 NYCRR 225-2.3: Compliance Certification

 1-6 6 NYCRR 227-1.3 (a): Compliance Certification

 29 6 NYCRR 227-1.3 (a): Compliance Certification

 30 6 NYCRR 227-1.3 (a): Compliance Certification

 1-7 6 NYCRR Subpart 227-2: Compliance Certification

 31 6 NYCRR Subpart 227-2: Compliance Certification

 1-8 6 NYCRR 227.2 (b) (1): Compliance Certification

 32 6 NYCRR 227.2 (b) (1): Compliance Certification

 33 6 NYCRR 243-1.6 (a): Permit Requirements

 34 6 NYCRR 243-1.6 (b): Monitoring requirements
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 3 FINAL

 35 6 NYCRR 243-1.6 (c): NOx Ozone Season Emission Requirements

 36 6 NYCRR 243-1.6 (d): Excess emission requirements

 37 6 NYCRR 243-1.6 (e): Recordkeeping and reporting requirements

 38 6 NYCRR 243-2.1: Authorization and responsibilities of CAIR 

 designated representative

 39 6 NYCRR 243-2.4: Certificate of representation

 40 6 NYCRR 243-8.1: General requirements

 41 6 NYCRR 243-8.1: Prohibitions

 42 6 NYCRR 243-8.5 (d): Quarterly reports

 43 6 NYCRR 243-8.5 (e): Compliance certification

 44 6 NYCRR Subpart 244-1: CAIR NOx Annual Trading Program General 

 Conditions

 45 6 NYCRR Subpart 244-2: Designated CAIR Representative

 46 6 NYCRR Subpart 244-8: Compliance Certification

 47 6 NYCRR Subpart 245-1: CAIR SO2 Trading Program General Provisions

 48 6 NYCRR Subpart 245-2: Designated CAIR Representative

 49 6 NYCRR Subpart 245-8: Compliance Certification

 1-9 6 NYCRR 249.3 (d): Compliance Certification

 50 40 CFR Part 72: Facility Subject to Title IV Acid Rain Regulations 

 and Permitting

 Emission Unit Level

 51 6 NYCRR Subpart 201-6: Emission Point Definition By Emission Unit

 52 6 NYCRR Subpart 201-6: Process Definition By Emission Unit

 EU=U-00001

 1-10 6 NYCRR 249.3 (f): Compliance Certification

 EU=U-00001,EP=00001

 1-11 6 NYCRR 227-1.3 (a): Compliance Certification

 53 6 NYCRR 227-1.3 (a): Compliance Certification

 EU=U-00002

 1-12 6 NYCRR 249.3 (a): Compliance Certification

 1-13 6 NYCRR 249.3 (a): Compliance Certification

 1-14 6 NYCRR 249.3 (a): Compliance Certification

 1-15 6 NYCRR 249.3 (a): Compliance Certification

 1-16 6 NYCRR 249.3 (f): Compliance Certification

 EU=U-00002,EP=00002

 1-17 6 NYCRR 227-1.3 (a): Compliance Certification

 54 6 NYCRR 227-1.3 (a): Compliance Certification

 STATE ONLY ENFORCEABLE CONDITIONS

 Facility Level

 55 ECL 19-0301: Contaminant List

 56 6 NYCRR 201-1.4: Unavoidable noncompliance and violations

 57 6 NYCRR 211.2: Air pollution prohibited

 1-18 6 NYCRR 211.2: Visible Emissions Limited

 1-19 6 NYCRR 211.2: Compliance Demonstration

 77 6 NYCRR 242-1.4 (b): Compliance Demonstration
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 4 FINAL

 78 6 NYCRR 242-1.5: CO2 Budget Trading Program - Excess emission 

 requirements

 79 6 NYCRR Subpart 242-4: Compliance Demonstration

 80 6 NYCRR Subpart 242-8: Compliance Demonstration

 81 6 NYCRR 242-8.5: Compliance Demonstration
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 5 FINAL

 FEDERALLY ENFORCEABLE CONDITIONS

 ** ** Facility Level  

 NOTIFICATION OF GENERAL PERMITTEE OBLIGATIONS

 The items listed below are not subject to the annual compliance certification

 requirements under Title V. Permittees may also have other obligations

 under regulations of general applicability.

Item A: Emergency Defense - 6 NYCRR 201-1.5

 An emergency constitutes an affirmative defense to an 

 action brought for noncompliance with emissions 

 limitations or permit conditions for all facilities in New

 York State.

 (a) The affirmative defense of emergency shall be 

 demonstrated through properly signed, contemporaneous 

 operating logs, or other relevant evidence that:

 (1) An emergency occurred and that the facility owner 

 and/or

 operator can identify the cause(s) of the 

 emergency;

 (2) The equipment at the permitted facility causing the

 emergency was at the time being properly operated;

 (3) During the period of the emergency the facility owner

 and/or operator took all reasonable steps to minimize 

 levels of emissions that exceeded the emission standards, 

 or other requirements in the permit; and

 (4) The facility owner and/or operator notified the 

 Department

 within two working days after the event occurred. This 

 notice must contain a description of the emergency, any 

 steps taken to mitigate emissions, and corrective actions 

 taken.

 (b) In any enforcement proceeding, the facility owner 

 and/or operator seeking to establish the occurrence of an 

 emergency has the burden of proof.

 (c) This provision is in addition to any emergency or 

 upset provision contained in any applicable requirement.

Item B: Public Access to Recordkeeping for Title V Facilities - 6

 NYCRR 201-1.10 (b)

 The Department will make available to the public any 

 permit application, compliance plan, permit, and 

 monitoring and compliance certification report pursuant to

 Section 503(e) of the Act, except for information entitled

 to confidential treatment pursuant to 6 NYCRR Part 616 - 

 Public Access to records and Section 114(c) of the Act.
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 6 FINAL

Item C: Timely Application for the Renewal of Title V Permits - 6

 NYCRR 201-6.3 (a) (4)

 Owners and/or operators of facilities having an issued 

 Title V permit shall submit a complete application at 

 least 180 days, but not more than eighteen months, prior 

 to the date of permit expiration for permit renewal 

 purposes.

Item D: Certification by a Responsible Official - 6 NYCRR 201-6.3

 (d) (12)

 Any application, form, report or compliance certification

 required to be submitted pursuant to the federally 

 enforceable portions of this permit shall contain a 

 certification of truth, accuracy and completeness by a 

 responsible official. This certification shall state that 

 based on information and belief formed after reasonable 

 inquiry, the statements and information in the document 

 are true, accurate, and complete.

Item E: Requirement to Comply With All Conditions - 6 NYCRR 

 201-6.5 (a) (2)

 The permittee must comply with all conditions of the 

 Title V facility permit. Any permit non-compliance 

 constitutes a violation of the Act and is grounds for 

 enforcement action; for permit termination, revocation and

 reissuance, or modification; or for denial of a permit 

 renewal application.

Item F: Permit Revocation, Modification, Reopening, Reissuance or

 Termination, and Associated Information Submission 

 Requirements - 6 NYCRR 201-6.5 (a) (3)

 This permit may be modified, revoked, reopened and 

 reissued, or terminated for cause. The filing of a request

 by the permittee for a permit modification, revocation and

 reissuance, or termination, or of a notification of 

 planned changes or anticipated noncompliance does not stay

 any permit condition.

Item G: Cessation or Reduction of Permitted Activity Not a 

 Defense - 6 NYCRR 201-6.5 (a) (5)

 It shall not be a defense for a permittee in an 

 enforcement action to claim that a cessation or reduction 

 in the permitted activity would have been necessary in 

 order to maintain compliance with the conditions of this 

 permit.

Item H: Property Rights - 6 NYCRR 201-6.5 (a) (6)

 This permit does not convey any property rights of any 

 sort or any exclusive privilege.
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 7 FINAL

Item I: Severability - 6 NYCRR 201-6.5 (a) (9)

 If any provisions, parts or conditions of this permit are

 found to be invalid or are the subject of a challenge, the

 remainder of this permit shall continue to be valid.

Item J: Permit Shield - 6 NYCRR 201-6.5 (g)

 All permittees granted a Title V facility permit shall be

 covered under the protection of a permit shield, except as

 provided under 6 NYCRR Subpart 201-6. Compliance with the

 conditions of the permit shall be deemed compliance with 

 any applicable requirements as of the date of permit 

 issuance, provided that such applicable requirements are 

 included and are specifically identified in the permit, or

 the Department, in acting on the permit application or 

 revision, determines in writing that other requirements 

 specifically identified are not applicable to the major 

 stationary source, and the permit includes the 

 determination or a concise summary thereof. Nothing herein

 shall preclude the Department from revising or revoking 

 the permit pursuant to 6 NYCRR Part 621 or from exercising

 its summary abatement authority. Nothing in this permit 

 shall alter or affect the following:

 i. The ability of the Department to seek to bring suit

 on behalf of the State of New York, or the Administrator 

 to seek to bring suit on behalf of the United States, to 

 immediately restrain any person causing or contributing to

 pollution presenting an imminent and substantial 

 endangerment to public health, welfare or the environment 

 to stop the emission of air pollutants causing or 

 contributing to such pollution;

 ii. The liability of a permittee of the Title V 

 facility for any violation of applicable requirements 

 prior to or at the time of permit issuance;

 iii. The applicable requirements of Title IV of the 

 Act;

 iv. The ability of the Department or the Administrator

 to obtain information from the permittee concerning the 

 ability to enter, inspect and monitor the facility.

Item K: Reopening for Cause - 6 NYCRR 201-6.5 (i)

 This Title V permit shall be reopened and revised under 

 any of the following circumstances:

 i. If additional applicable requirements under the Act

 become applicable where this permit's remaining term is 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 8 FINAL

 three or more years, a reopening shall be completed not 

 later than 18 months after promulgation of the applicable 

 requirement. No such reopening is required if the 

 effective date of the requirement is later than the date 

 on which this permit is due to expire, unless the original

 permit or any of its terms and conditions has been 

 extended by the Department pursuant to the provisions of 

 Part 201-6.7 and Part 621.

 ii. The Department or the Administrator determines 

 that the permit contains a material mistake or that 

 inaccurate statements were made in establishing the 

 emissions standards or other terms or conditions of the 

 permit.

 iii. The Department or the Administrator determines 

 that the Title V permit must be revised or reopened to 

 assure compliance with applicable requirements.

 iv. If the permitted facility is an "affected source" 

 subject to the requirements of Title IV of the Act, and 

 additional requirements (including excess emissions 

 requirements) become applicable. Upon approval by the 

 Administrator, excess emissions offset plans shall be 

 deemed to be incorporated into the permit.

 Proceedings to reopen and issue Title V facility permits 

 shall follow the same procedures as apply to initial 

 permit issuance but shall affect only those parts of the 

 permit for which cause to reopen exists.

 Reopenings shall not be initiated before a notice of such

 intent is provided to the facility by the Department at 

 least thirty days in advance of the date that the permit 

 is to be reopened, except that the Department may provide

 a shorter time period in the case of an emergency.

Item L: Permit Exclusion - ECL 19-0305

 The issuance of this permit by the Department and the 

 receipt thereof by the Applicant does not and shall not be

 construed as barring, diminishing, adjudicating or in any 

 way affecting any legal, administrative or equitable 

 rights or claims, actions, suits, causes of action or 

 demands whatsoever that the Department may have against 

 the Applicant for violations based on facts and 

 circumstances alleged to have occurred or existed prior to

 the effective date of this permit, including, but not 

 limited to, any enforcement action authorized pursuant to 

 the provisions of applicable federal law, the 

 Environmental Conservation Law of the State of New York 

 (ECL) and Chapter III of the Official Compilation of the 

 Codes, Rules and Regulations of the State of New York 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 9 FINAL

 (NYCRR). The issuance of this permit also shall not in any

 way affect pending or future enforcement actions under the

 Clean Air Act brought by the United States or any person.

Item M: Federally Enforceable Requirements - 40 CFR 70.6 (b)

 All terms and conditions in this permit required by the 

 Act or any applicable requirement, including any 

 provisions designed to limit a facility's potential to 

 emit, are enforceable by the Administrator and citizens 

 under the Act. The Department has, in this permit, 

 specifically designated any terms and conditions that are 

 not required under the Act or under any of its applicable 

 requirements as being enforceable under only state 

 regulations.

 MANDATORY FEDERALLY ENFORCEABLE PERMIT CONDITIONS 

 SUBJECT TO ANNUAL CERTIFICATIONS AT ALL TIMES

 The following federally enforceable permit conditions are mandatory for all

 Title V permits and are subject to annual compliance certification 

 requirements at all times.

Condition 1: Acceptable Ambient Air Quality

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 200.6

Item 1.1:

Notwithstanding the provisions of 6 NYCRR Chapter III, Subchapter A, no person shall allow or

permit any air contamination source to emit air contaminants in quantities which alone or in

combination with emissions from other air contamination sources would contravene any

applicable ambient air quality standard and/or cause air pollution. In such cases where

contravention occurs or may occur, the Commissioner shall specify the degree and/or method of

emission control required.

Condition 2: Fees

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 201-6.5 (a) (7)

Item 2.1:

The owner and/or operator of a stationary source shall pay fees to the Department consistent

with the fee schedule authorized by ECL 72-0303.

Condition 3: Recordkeeping and reporting of compliance monitoring

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 201-6.5 (c)

Item 3.1:
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 10 FINAL

The following information must be included in any required compliance monitoring records and

reports:

(i) The date, place, and time of sampling or measurements;

(ii) The date(s) analyses were performed;

(iii)The company or entity that performed the analyses;

(iv) The analytical techniques or methods used including quality assurance and quality control

procedures if required;

(v) The results of such analyses including quality assurance data where required; and

(vi) The operating conditions as existing at the time of sampling or measurement.

Any deviation from permit requirements must be clearly identified in all records and reports. 

Reports must be certified by a responsible official, consistent with Section 201-6.3 of this Part

201.

Condition 4: Monitoring, Related Recordkeeping, and Reporting 

 Requirements.

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 201-6.5 (c) (2)

Item 4.1:

Compliance monitoring and recordkeeping shall be conducted according to the terms and

conditions contained in this permit and shall follow all quality assurance requirements found in

applicable regulations. Records of all monitoring data and support information must be retained

for a period of at least 5 years from the date of the monitoring, sampling, measurement, report,

or application. Support information includes all calibration and maintenance records and all

original strip-chart recordings for continuous monitoring instrumentation, and copies of all

reports required by the permit. 

Condition 5: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 201-6.5 (c) (3) (ii)

Item 5.1:

The Compliance Certification activity will be performed for the Facility.

Item 5.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 To meet the requirements of this facility permit with 

 respect to reporting, the permittee must:

 Submit reports of any required monitoring at a minimum 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 11 FINAL

 frequency of every 6 months, based on a calendar year 

 reporting schedule. These reports shall be submitted to 

 the Department within 30 days after the end of a reporting

 period. All instances of deviations from permit 

 requirements must be clearly identified in such reports. 

 All required reports must be certified by the responsible 

 official for this facility.

 Notify the Department and report permit deviations and 

 incidences of noncompliance stating the probable cause of 

 such deviations, and any corrective actions or preventive 

 measures taken. Where the underlying applicable 

 requirement contains a definition of prompt or otherwise 

 specifies a time frame for reporting deviations, that 

 definition or time frame shall govern. Where the 

 underlying applicable requirement fails to address the 

 time frame for reporting deviations, reports of deviations

 shall be submitted to the permitting authority based on 

 the following schedule:

 (1) For emissions of a hazardous air pollutant (as 

 identified in an applicable regulation) that continue for 

 more than an hour in excess of permit requirements, the 

 report must be made within 24 hours of the 

 occurrence.

 (2) For emissions of any regulated air pollutant, 

 excluding those listed in paragraph (1) of this section, 

 that continue for more than two hours in excess of permit 

 requirements, the report must be made within 48 

 hours.

 (3) For all other deviations from permit requirements, 

 the report shall be contained in the 6 month monitoring 

 report required above.

 (4) This permit may contain a more stringent reporting 

 requirement than required by paragraphs (1), (2) or (3) 

 above. If more stringent reporting requirements have been

 placed in this permit or exist in applicable requirements 

 that apply to this facility, the more stringent reporting 

 requirement shall apply.

 If above paragraphs (1) or (2) are met, the source must 

 notify the permitting authority by telephone during normal

 business hours at the Regional Office of jurisdiction for 

 this permit, attention Regional Air Pollution Control 

 Engineer (RAPCE) according to the timetable listed in 

 paragraphs (1) and (2) of this section. For deviations 

 and incidences that must be reported outside of normal 

 business hours, on weekends, or holidays, the DEC Spill 

 Hotline phone number at 1-800-457-7362 shall be used. A 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 12 FINAL

 written notice, certified by a responsible official 

 consistent with 6 NYCRR Part 201-6.3(d)(12), must be 

 submitted within 10 working days of an occurrence for 

 deviations reported under (1) and (2). All deviations 

 reported under paragraphs (1) and (2) of this section must

 also be identified in the 6 month monitoring report 

 required above.

 The provisions of 6 NYCRR 201-1.4 shall apply if the 

 permittee seeks to have a violation excused unless 

 otherwise limited by regulation. In order to have a 

 violation of a federal regulation (such as a new source 

 performance standard or national emissions standard for 

 hazardous air pollutants) excused, the specific federal 

 regulation must provide for an affirmative defense during 

 start-up, shutdowns, malfunctions or upsets. 

 Notwithstanding any recordkeeping and reporting 

 requirements in 6 NYCRR 201-1.4, reports of any deviations

 shall not be on a less frequent basis than the reporting 

 periods described in paragraphs (1) and (4) above. 

 In the case of any condition contained in this permit with

 a reporting requirement of "Upon request by regulatory 

 agency" the permittee shall include in the semiannual 

 report, a statement for each such condition that the 

 monitoring or recordkeeping was performed as required or 

 requested and a listing of all instances of deviations 

 from these requirements.

 In the case of any emission testing performed during the 

 previous six month reporting period, either due to a 

 request by the Department, EPA, or a regulatory 

 requirement, the permittee shall include in the semiannual

 report a summary of the testing results and shall indicate

 whether or not the Department or EPA has approved the 

 results.

 All semiannual reports shall be submitted to the 

 Administrator (or his or her representative) as well as 

 two copies to the Department (one copy to the regional air

 pollution control engineer (RAPCE) in the regional office 

 and one copy to the Bureau of Quality Assurance (BQA) in 

 the DEC central office). Mailing addresses for the above 

 referenced persons are contained in the monitoring 

 condition for 6 NYCRR Part 201-6.5(e), contained elsewhere

 in this permit.

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 7/30/2011.

Subsequent reports are due every 6 calendar month(s).
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 13 FINAL

Condition 6: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 202-2.1

Item 6.1:

The Compliance Certification activity will be performed for the Facility.

Item 6.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Emission statements shall be submitted on or before April

 15th each year for emissions of the previous calendar 

 year. Statements are to be mailed to: New York State 

 Department of Environmental Conservation, Division of Air 

 Resources, Bureau of Air Quality Planning, 625 Broadway, 

 Albany NY 12233-3251

Monitoring Frequency: ANNUALLY

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due by April 15th for previous calendar year

Condition 7: Recordkeeping requirements

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 202-2.5

Item 7.1:

(a) The following records shall be maintained for at least five years:

 (1) a copy of each emission statement submitted to the department; and

 (2) records indicating how the information submitted in the emission

statement was determined, including any calculations, data, measurements, and estimates used.

(b) These records shall be made available at the facility to the representatives of the

department upon request during normal business hours.

Condition 8: Open Fires Prohibited at Industrial and Commercial Sites

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR Part 215

Item 8.1:

No person shall burn, cause, suffer, allow or permit the burning in an open fire of garbage,

refuse, rubbish for salvage, or rubbish generated by industrial or commercial activities.

Condition 9: Open Fires - Prohibitions

 Effective between the dates of 02/24/2011 and 02/23/2016
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 14 FINAL

 Applicable Federal Requirement:6 NYCRR 215.2

Item 9.1: 

Except as allowed by Title 6 NYCRR Section 215.3, no person shall burn, cause, suffer, allow

or permit the burning of any materials in an open fire.

Item 9.2

Per Section 215.3, burning in an open fire, provided it is not contrary to other law or regulation,

will be allowed as follows:

(a) On-site burning in any town with a total population less than 20,000 of downed limbs and

branches (including branches with attached leaves or needles) less than six inches in diameter

and eight feet in length between May 15th and the following March 15th. For the purposes of

this subdivision, the total population of a town shall include the population of any village or

portion thereof located within the town. However, this subdivision shall not be construed to

allow burning within any village.

(b) Barbecue grills, maple sugar arches and similar outdoor cooking devices when actually used

for cooking or processing food.

(c) Small fires used for cooking and camp fires provided that only charcoal or untreated wood is

used as fuel and the fire is not left unattended until extinguished.

(d) On-site burning of agricultural wastes as part of a valid agricultural operation on contiguous

agricultural lands larger than five acres actively devoted to agricultural or horticultural use,

provided such waste is actually grown or generated on those lands and such waste is capable of

being fully burned within a 24-hour period.

(e) The use of liquid petroleum fueled smudge pots to prevent frost damage to crops.

(f) Ceremonial or celebratory bonfires where not otherwise prohibited by law, provided that only

untreated wood or other agricultural products are used as fuel and the fire is not left unattended

until extinguished.

(g) Small fires that are used to dispose of a flag or religious item, and small fires or other smoke

producing process where not otherwise prohibited by law that are used in connection with a

religious ceremony.

(h) Burning on an emergency basis of explosive or other dangerous or contraband materials by

police or other public safety organization.

(i) Prescribed burns performed according to Part 194 of this Title.

(j) Fire training, including firefighting, fire rescue, and fire/arson investigation training,

performed under applicable rules and guidelines of the New York State Department of State's

Office of Fire Prevention and Control. For fire training performed on acquired structures, the

structures must be emptied and stripped of any material that is toxic, hazardous or likely to emit

toxic smoke (such as asbestos, asphalt shingles and vinyl siding or other vinyl products) prior to

burning and must be at least 300 feet from other occupied structures. No more than one structure

per lot or within a 300 foot radius (whichever is bigger) may be burned in a training exercise.

(k) Individual open fires as approved by the Director of the Division of Air Resources as may be

required in response to an outbreak of a plant or animal disease upon request by the

commissioner of the Department of Agriculture and Markets, or for the destruction of invasive

plant and insect species.

(l) Individual open fires that are otherwise authorized under the environmental conservation law,

or by rule or regulation of the Department.

 MANDATORY FEDERALLY ENFORCEABLE PERMIT CONDITIONS 

 SUBJECT TO ANNUAL CERTIFICATIONS ONLY IF APPLICABLE
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 15 FINAL

 The following federally enforceable permit conditions are mandatory for all 

 Title V permits and are subject to annual compliance certification 

 requirements only if effectuated during the reporting period.

 [NOTE: The corresponding annual compliance certification for 

 those conditions not effectuated during the reporting period shall 

 be specified as "not applicable".]

Condition 10: Maintenance of Equipment

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 200.7

Item 10.1:

Any person who owns or operates an air contamination source which is equipped with an

emission control device shall operate such device and keep it in a satisfactory state of

maintenance and repair in accordance with ordinary and necessary practices, standards and

procedures, inclusive of manufacturer's specifications, required to operate such device

effectively.

Condition 11: Recycling and Salvage

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 201-1.7

Item 11.1:

Where practical, any person who owns or operates an air contamination source shall recycle or

salvage air contaminants collected in an air cleaning device according to the requirements of the

ECL.

Condition 12: Prohibition of Reintroduction of Collected Contaminants to

 the air

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 201-1.8

Item 12.1:

No person shall unnecessarily remove, handle or cause to be handled, collected air contaminants

from an air cleaning device for recycling, salvage or disposal in a manner that would reintroduce

them to the outdoor atmosphere.

Condition 13: Exempt Sources - Proof of Eligibility

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 201-3.2 (a)

Item 13.1:

The owner and/or operator of an emission source or unit that is eligible to be exempt may be

required to certify that it operates within the specific criteria described in this Subpart. The

owner or operator of any such emission source must maintain all required records on-site for a

period of five years and make them available to representatives of the department upon request.

Department representatives must be granted access to any facility which contains emission

sources or units subject to this Subpart, during normal operating hours, for the purpose of
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 16 FINAL

determining compliance with this and any other State and Federal air pollution control

requirements, regulations, or law.

Condition 14: Trivial Sources - Proof of Eligibility

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 201-3.3 (a)

Item 14.1:

The owner and/or operator of an emission source or unit that is listed as being trivial in this Part

may be required to certify that it operates within the specific criteria described in this Subpart.

The owner or operator of any such emission source must maintain all required records on-site for

a period of five years and make them available to representatives of the department upon

request. Department representatives must be granted access to any facility which contains

emission sources or units subject to this Subpart, during normal operating hours, for the purpose

of determining compliance with this and any other State and Federal air pollution control

requirements, regulations, or law.

Condition 15: Standard Requirement - Provide Information

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 201-6.5 (a) (4)

Item 15.1:

The owner and/or operator shall furnish to the department, within a reasonable time, any

information that the department may request in writing to determine whether cause exists for

modifying, revoking and reissuing, or terminating the permit or to determine compliance with

the permit. Upon request, the permittee shall also furnish to the department copies of records

required to be kept by the permit or, for information claimed to be confidential, the permittee

may furnish such records directly to the administrator along with a claim of confidentiality, if the

administrator initiated the request for information or otherwise has need of it.

Condition 16: General Condition - Right to Inspect

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 201-6.5 (a) (8)

Item 16.1:

The department or an authorized representative shall be allowed upon presentation of credentials

 and other documents as may be required by law to:

(i) enter upon the permittee's premises where a facility subject to the permitting requirements of

this Subpart is located or emissions-related activity is conducted, or where records must be kept

under the conditions of the permit;

(ii) have access to and copy, at reasonable times, any records that must be kept under the

conditions of the permit;

(iii) inspect at reasonable times any emission sources, equipment (including monitoring and air

pollution control equipment), practices, and operations regulated or required under the permit;

and
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 17 FINAL

(iv) sample or monitor at reasonable times substances or parameters for the purpose of assuring

compliance with the permit or applicable requirements.

Condition 17: Standard Requirements - Progress Reports

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 201-6.5 (d) (5)

Item 17.1:

Progress reports consistent with an applicable schedule of compliance are to be submitted at

least semiannually, or at a more frequent period if specified in the applicable requirement or by

the department. Such progress reports shall contain the following:

(i) dates for achieving the activities, milestones, or compliance required in the schedule of

compliance, and dates when such activities, milestones or compliance were achieved; and

(ii) an explanation of why any dates in the schedule of compliance were not or will not be met,

and any preventive or corrective measures adopted.

Condition 18: Off Permit Changes

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 201-6.5 (f) (6)

Item 18.1:

No permit revision will be required for operating changes that contravene an express permit

term, provided that such changes would not violate applicable requirements as defined under this

Part or contravene federally enforceable monitoring (including test methods), recordkeeping,

reporting, or compliance certification permit terms and conditions. Such changes may be made

without requiring a permit revision, if the changes are not modifications under any provision of

title I of the act and the changes do not exceed the emissions allowable under the permit

(whether expressed therein as a rate of emissions or in terms of total emissions) provided that the

facility provides the administrator and the department with written notification as required below

in advance of the proposed changes within a minimum of seven days. The facility owner or

operator, and the department shall attach each such notice to their copy of the relevant permit.

(i) For each such change, the written notification required above shall include a brief description

of the change within the permitted facility, the date on which the change will occur, any change

in emissions, and any permit term or condition that is no longer applicable as a result of the

change.

(ii) The permit shield described in section 6 NYCRR 201-6.6 shall not apply to any change

made pursuant to this paragraph.

Condition 19: Required Emissions Tests

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 202-1.1

Item 19.1:

For the purpose of ascertaining compliance or non-compliance with any air pollution control

code, rule or regulation, the commissioner may require the person who owns such air
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 18 FINAL

contamination source to submit an acceptable report of measured emissions within a stated time.

Condition 20: Visible Emissions Limited

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 211.3

Item 20.1:

Except as permitted by a specific part of this Subchapter and for open fires for which a restricted

burning permit has been issued, no person shall cause or allow any air contamination source to

emit any material having an opacity equal to or greater than 20 percent (six minute average)

except for one continuous six-minute period per hour of not more than 57 percent opacity.

Condition 21: Accidental release provisions.

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:40 CFR Part 68

Item 21.1:

If a chemical is listed in Tables 1,2,3 or 4 of 40 CFR §68.130 is present in a process in quantities

greater than the threshold quantity listed in Tables 1,2,3 or 4, the following requirements will

apply:

a) The owner or operator shall comply with the provisions of 40 CFR Part 68 and;

b) The owner or operator shall submit at the time of permit issuance (if not previously

submitted) one of the following, if such quantities are present: 

1) A compliance schedule for meeting the requirements of 40 CFR Part 68 by the date provided

in 40 CFR §68.10(a) or,

2) A certification statement that the source is in compliance with all requirements of 40 CFR

Part 68, including the registration and submission of the Risk Management Plan. Information

should be submitted to:

Risk Management Plan Reporting Center

C/O CSC

8400 Corporate Dr

Carrollton, Md. 20785

Condition 22: Recycling and Emissions Reduction

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:40CFR 82, Subpart F

Item 22.1:

The permittee shall comply with all applicable provisions of 40 CFR Part 82.

 The following conditions are subject to annual compliance certification 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 19 FINAL

 requirements for Title V permits only.

Condition 23: Emission Unit Definition

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR Subpart 201-6

Item 23.1(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00001 

 Emission Unit Description: 

 This unit is a 185 mwe turbine/generator boiler set 

 firing #1, #2 and #6 fuel oils and pipeline natural gas. 

 In addition, this boiler may co-fire waste fuel for energy

 recovery and citrosolv for incineration. Exhaust is 

 through emission point 00001.

 Building(s): BOILERBLD1

Item 23.2(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00002 

 Emission Unit Description: 

 This unit is a 185 mwe turbine/generator boiler set 

 firing #1, #2 and #6 fuel oils and pipeline natural gas. 

 In addition, this boiler may co-fire waste oil for energy 

 recovery and citrosolv for incineration. Exhaust is 

 through emission point 00002.

 Building(s): BOILERBLD2

Item 23.3(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00003 

 Emission Unit Description: 

 This unit is an industrial steam boiler used to supply 

 auxiliary steam loads required by all onsite facilities.

 Building(s): HOUSEBOILE

Item 23.4(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00004 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the long 

 island electric distribution system. This unit is a "black

 start" combustion turbine designed to provide sufficient 

 power to bring the entire power station back on line 

 following a catastrophic system collapse. A diesel engine,
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 20 FINAL

 emission point 000S4, emission unit U000S4 is utilized to 

 start this combustion turbine.

 Building(s): CT#1

Item 23.5(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00005 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the Long 

 Island Electric distribution system.

 Building(s): CT#2

Item 23.6(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00006 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the Long 

 Island Electric distribution system.

 Building(s): CT#3

Item 23.7(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00007 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the Long 

 Island Electric distribution system.

 Building(s): CT#4

Item 23.8(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00008 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the long 

 island electric distribution system. This unit is a "black

 start" combustion turbine designed to provide sufficient 

 power to bring the entire power station back on line 

 following a catastrophic system collapse. A diesel engine,

 emission point 000S8, emission unit 000S8 is utilized to 

 start this combustion engine.

 Building(s): CT#5

Item 23.9(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 21 FINAL

 Emission Unit: U-00009 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the Long 

 Island Electric distribution system.

 Building(s): CT#6

Item 23.10(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00010 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the Long 

 Island Electric distribution system.

 Building(s): CT#7

Item 23.11(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00011 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the Long 

 Island Electric distribution system.

 Building(s): CT#8

Item 23.12(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00012 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the long 

 island electric distribution system. This unit is paired 

 with emission unit U00013 to operate a single generator. 

 The emission point, emission unit, emission source and 

 processes are completely independent, the generator is the

 only common component. Inlet water fogging may be utilized

 at maximum load to reduce NOx formation.

 Building(s): CT#9

Item 23.13(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00013 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the long 

 island electric distribution system. This unit is paired 

 with emission unit U00012 to operate a single generator. 

 The emission point, emission unit, emission source and 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 22 FINAL

 processes are completely independent, the generator is the

 only common component. Inlet water fogging may be utilized

 at maximum load to reduce NOx formation.

 Building(s): CT#9

Item 23.14(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00014 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the long 

 island electric distribution system. This unit is paired 

 with emission unit U00015 to operate a single generator. 

 The emission point, emission unit, emission source and 

 processes are completely independent, the generator is the

 only common component. Inlet water fogging may be utilized

 at maximum load to reduce NOx formation.

 Building(s): CT#10

Item 23.15(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00015 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the long 

 island electric distribution system. This unit is paired 

 with emission unit U00014 to operate a single generator. 

 The emission point, emission unit, emission source and 

 processes are completely independent, the generator is the

 only common component. Inlet water fogging may be utilized

 at maximum load to reduce NOx formation.

 Building(s): CT#10

Item 23.16(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00016 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the long 

 island electric distribution system. This unit is paired 

 with emission unit U00017 to operate a single generator. 

 The emission point, emission unit, emission source and 

 processes are completely independent, the generator is the

 only common component. Inlet water fogging may be utilized

 at maximum load to reduce NOx formation.

 Building(s): CT#11

Item 23.17(From Mod 1):
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 23 FINAL

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00017 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the long 

 island electric distribution system. This unit is paired 

 with emission unit U00016 to operate a single generator. 

 The emission point, emission unit, emission source and 

 processes are completely independent, the generator is the

 only common component. Inlet water fogging may be utilized

 at maximum load to reduce NOx formation.

 Building(s): CT#11

Item 23.18(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00018 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the long 

 island electric distribution system. This unit is paired 

 with emission unit U00019 to operate a single generator. 

 The emission point, emission unit, emission source and 

 processes are completely independent, the generator is the

 only common component. Inlet water fogging may be utilized

 at maximum load to reduce NOx formation.

 Building(s): CT#12

Item 23.19(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00019 

 Emission Unit Description: 

 This unit is a combustion turbine used to supply peak 

 generation capacity, as required to support the long 

 island electric distribution system. This unit is paired 

 with emission unit U00018 to operate a single generator. 

 The emission point, emission unit, emission source and 

 processes are completely independent, the generator is the

 only common component. Inlet water fogging may be utilized

 at maximum load to reduce NOx formation.

 Building(s): CT#12

Item 23.20(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-000S4 

 Emission Unit Description: 

 This unit is a 340 hp diesel engine used to start the 

 black start combustion turbine, designated emission unit 

 U00004. This unit only operates during startup of the 

 combustion turbine, generally less than 15 minutes per 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 24 FINAL

 event.

 Building(s): CT#1

Item 23.21(From Mod 1):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-000S8 

 Emission Unit Description: 

 This unit is a 340 hp diesel engine used to start the 

 "black start" combustion turbine, designated emission unit

 U00008. This unit only operates during startup of the 

 combustion turbine, generally less than 15 minutes per 

 event

 Building(s): CT#5

Condition 24: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 201-6.5 (e)

Item 24.1:

The Compliance Certification activity will be performed for the Facility.

Item 24.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Requirements for compliance certifications with terms and

 conditions contained in this facility permit include the 

 following:

 i. Compliance certifications shall contain:

 - the identification of each term or condition of the 

 permit that is the basis of the certification;

 - the compliance status;

 - whether compliance was continuous or intermittent;

 - the method(s) used for determining the compliance status

 of the facility, currently and over the reporting period 

 consistent with the monitoring and related recordkeeping 

 and reporting requirements of this permit;

 - such other facts as the Department may require to 

 determine the compliance status of the facility as 

 specified in any special permit terms or conditions; 

 and

 - such additional requirements as may be specified 

 elsewhere in this permit related to compliance 

 certification.

 ii. The responsible official must include in the annual 

 certification report all terms and conditions contained in
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 25 FINAL

 this permit which are identified as being subject to 

 certification, including emission limitations, standards, 

 or work practices. That is, the provisions labeled herein

 as "Compliance Certification" are not the only provisions 

 of this permit for which an annual certification is 

 required.

 iii. Compliance certifications shall be submitted 

 annually. Certification reports are due 30 days after the

 anniversary date of four consecutive calendar quarters. 

 The first report is due 30 days after the calendar quarter

 that occurs just prior to the permit anniversary date, 

 unless another quarter has been acceptable by the 

 Department.

 iv. All compliance certifications shall be submitted to 

 the Administrator (or his or her representative) as well 

 as two copies to the Department (one copy to the regional 

 air pollution control engineer (RAPCE) in the regional 

 office and one copy to the Bureau of Quality Assurance 

 (BQA) in the DEC central office). Please send annual 

 compliance certifications to Chief of the Stationary 

 Source Compliance Section, the Region 2 EPA representative

 for the Administrator, at the following address:

 USEPA Region 2

 Air Compliance Branch

 290 Broadway

 New York, NY 10007-1866

 

 The address for the RAPCE is as follows:

 NYSDEC- Region 1 Headquarters

 Stony Brook University

 50 Circle Road

 Stony Brook, NY 11790-3409

 The address for the BQA is as follows:

 NYSDEC 

 Bureau of Quality Assurance

 625 Broadway

 Albany, NY 12233-3258

Monitoring Frequency: ANNUALLY

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2012.

Subsequent reports are due on the same day each year

Condition 1-1: Air pollution prohibited

 Effective between the dates of 03/27/2012 and 02/23/2016
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 26 FINAL

 Applicable Federal Requirement:6 NYCRR 211.1

Item 1-1.1:

No person shall cause or allow emissions of air contaminants to the outdoor atmosphere of such

quantity, characteristic or duration which are injurious to human, plant or animal life or to

property, or which unreasonably interfere with the comfortable enjoyment of life or property.

Notwithstanding the existence of specific air quality standards or emission limits, this

prohibition applies, but is not limited to, any particulate, fume, gas, mist, odor, smoke, vapor,

pollen, toxic or deleterious emission, either alone or in combination with others.

Condition 1-2: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 225-1.2 (a) (2)

Item 1-2.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 007446-09-5 SULFUR DIOXIDE

Item 1-2.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: WORK PRACTICE INVOLVING SPECIFIC 

 OPERATIONS

Monitoring Description: 

 This unit is restricted to burning low sulfur fuel in 

 order to limit SO2 emissions. All fuel is purchased on 

 specification. Source tank to be verified in compliance 

 with limit. Deliveries may continue until fuel added to 

 source tank.

Work Practice Type: PARAMETER OF PROCESS MATERIAL

Process Material: NUMBER 1 OIL

Parameter Monitored: SULFUR CONTENT

Upper Permit Limit: 0.37 percent by weight

Reference Test Method: ASTM D-4294

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Averaging Method: MAXIMUM - NOT TO BE EXCEEDED AT ANY 

 TIME (INSTANTANEOUS/DISCRETE OR GRAB)

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2013.

Subsequent reports are due every 12 calendar month(s).

Condition 1-3: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 27 FINAL

 Applicable Federal Requirement:6 NYCRR 225-1.2 (a) (2)

Item 1-3.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 007446-09-5 SULFUR DIOXIDE

Item 1-3.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: WORK PRACTICE INVOLVING SPECIFIC 

 OPERATIONS

Monitoring Description: 

 This unit is restricted to burning low sulfur fuel in 

 order to limit SO2 emissions. All fuel is purchased on 

 specification. Source tank to be verified in compliance 

 with limit. Deliveries may continue until fuel added to 

 source tank.

Work Practice Type: PARAMETER OF PROCESS MATERIAL

Process Material: NUMBER 6 OIL

Parameter Monitored: SULFUR CONTENT

Upper Permit Limit: 0.37 percent by weight

Reference Test Method: ASTM D-4294

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Averaging Method: MAXIMUM - NOT TO BE EXCEEDED AT ANY 

 TIME (INSTANTANEOUS/DISCRETE OR GRAB)

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2013.

Subsequent reports are due every 12 calendar month(s).

Condition 1-4: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 225-1.2 (a) (2)

Item 1-4.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 007446-09-5 SULFUR DIOXIDE

Item 1-4.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: WORK PRACTICE INVOLVING SPECIFIC 

 OPERATIONS

Monitoring Description: 

 This unit is restricted to burning low sulfur fuel in 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 28 FINAL

 order to limit SO2 emissions. All fuel is purchased on 

 specification. Source tank to be verified in compliance 

 with limit. Deliveries may continue until fuel added to 

 source tank.

Work Practice Type: PARAMETER OF PROCESS MATERIAL

Process Material: NUMBER 2 OIL

Parameter Monitored: SULFUR CONTENT

Upper Permit Limit: 0.37 percent by weight

Reference Test Method: ASTM D-4294

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Averaging Method: MAXIMUM - NOT TO BE EXCEEDED AT ANY 

 TIME (INSTANTANEOUS/DISCRETE OR GRAB)

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2013.

Subsequent reports are due every 12 calendar month(s).

Condition 25: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 225-1.2 (a) (2)

Item 25.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 007446-09-5 SULFUR DIOXIDE

Item 25.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: WORK PRACTICE INVOLVING SPECIFIC 

 OPERATIONS

Monitoring Description: 

 This unit is restricted to burning low sulfur fuel in 

 order to limit SO2 emissions. All fuel is purchased on 

 specification. Source tank to be verified in compliance 

 with limit. Deliveries may continue until fuel added to 

 source tank.

Work Practice Type: PARAMETER OF PROCESS MATERIAL

Process Material: NUMBER 1 OIL

Parameter Monitored: SULFUR CONTENT

Upper Permit Limit: 0.37 percent by weight

Reference Test Method: ASTM D-4294

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Averaging Method: MAXIMUM - NOT TO BE EXCEEDED AT ANY 

 TIME (INSTANTANEOUS/DISCRETE OR GRAB)

Reporting Requirements: ANNUALLY (CALENDAR)
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 29 FINAL

Reports due 30 days after the reporting period.

The initial report is due 1/30/2012.

Subsequent reports are due every 12 calendar month(s).

Condition 26: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 225-1.2 (a) (2)

Item 26.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 007446-09-5 SULFUR DIOXIDE

Item 26.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: WORK PRACTICE INVOLVING SPECIFIC 

 OPERATIONS

Monitoring Description: 

 This unit is restricted to burning low sulfur fuel in 

 order to limit SO2 emissions. All fuel is purchased on 

 specification. Source tank to be verified in compliance 

 with limit. Deliveries may continue until fuel added to 

 source tank.

Work Practice Type: PARAMETER OF PROCESS MATERIAL

Process Material: NUMBER 2 OIL

Parameter Monitored: SULFUR CONTENT

Upper Permit Limit: 0.37 percent by weight

Reference Test Method: ASTM D-4294

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Averaging Method: MAXIMUM - NOT TO BE EXCEEDED AT ANY 

 TIME (INSTANTANEOUS/DISCRETE OR GRAB)

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2012.

Subsequent reports are due every 12 calendar month(s).

Condition 27: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 225-1.2 (a) (2)

Item 27.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 007446-09-5 SULFUR DIOXIDE
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 30 FINAL

Item 27.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: WORK PRACTICE INVOLVING SPECIFIC 

 OPERATIONS

Monitoring Description: 

 This unit is restricted to burning low sulfur fuel in 

 order to limit SO2 emissions. All fuel is purchased on 

 specification. Source tank to be verified in compliance 

 with limit. Deliveries may continue until fuel added to 

 source tank.

Work Practice Type: PARAMETER OF PROCESS MATERIAL

Process Material: NUMBER 6 OIL

Parameter Monitored: SULFUR CONTENT

Upper Permit Limit: 0.37 percent by weight

Reference Test Method: ASTM D-4294

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Averaging Method: MAXIMUM - NOT TO BE EXCEEDED AT ANY 

 TIME (INSTANTANEOUS/DISCRETE OR GRAB)

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2012.

Subsequent reports are due every 12 calendar month(s).

Condition 1-5: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 225-2.3

Item 1-5.1:

The Compliance Certification activity will be performed for the Facility.

Item 1-5.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Combustion of waste fuel is in accordance with procedures

 and practices previously established with the NYSDEC . 

 Waste fuel is tested for compliance with 6NYCRR Part 

 225-2.3 and co-fired with primary boiler fuel at a maximum

 rate equivalent to 5% of the total heat input into the 

 boiler. Lead, PCB's, and total halogens are tested on 

 every delivery from off site. ( only Nationalgrid waste 

 fuel is accepted ). Monthly samples are collected and 

 analyzed from each waste fuel tank on site. Analysis for 

 sulfur and heat content have been waived by the NYSDEC 

 since the co-firing rate restrictions insures that the "as

 burned" waste fuel in the boiler is always within the 

 limitations of Part 225-2.3. Lead, PCB's and halogens 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 31 FINAL

 limitations are complied with on an "as delivered" and/or 

 "as generated" basis.

Reference Test Method: ASTM

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Averaging Method: AVERAGING METHOD AS PER REFERENCE TEST

 METHOD INDICATED

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2012.

Subsequent reports are due every 3 calendar month(s).

Condition 28: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 225-2.3

Item 28.1:

The Compliance Certification activity will be performed for the Facility.

Item 28.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Combustion of waste fuel is in accordance with procedures

 and practices previously established with the NYSDEC . 

 Waste fuel is tested for compliance with 6NYCRR Part 

 225-2.3 and co-fired with primary boiler fuel at a maximum

 rate equivalent to 5% of the total heat input into the 

 boiler. Lead, PCB's, and total halogens are tested on 

 every delivery from off site. ( only Nationalgrid waste 

 fuel is accepted ). Monthly samples are collected and 

 analyzed from each waste fuel tank on site. Analysis for 

 sulfur and heat content have been waived by the NYSDEC 

 since the co-firing rate restrictions insures that the "as

 burned" waste fuel in the boiler is always within the 

 limitations of Part 225-2.3. Lead, PCB's and halogens 

 limitations are complied with on an "as delivered" and/or 

 "as generated" basis.

Reference Test Method: ASTM

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Averaging Method: AVERAGING METHOD AS PER REFERENCE TEST

 METHOD INDICATED

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2011.

Subsequent reports are due every 3 calendar month(s).
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 32 FINAL

Condition 1-6: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 227-1.3 (a)

Item 1-6.1:

The Compliance Certification activity will be performed for the Facility.

Item 1-6.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: MONITORING OF PROCESS OR CONTROL 

 DEVICE PARAMETERS AS SURROGATE

Monitoring Description: 

 Visible emissions at the facility are limited to 20 

 percent opacity , except for one six minute period per 

 hour not to exceed 27 percent, based upon the six minute 

 average as stated in Reference Method 9 Appendix A 

 40CFR60. This condition applies to emission units 4 thru 

 19. Owner or operator shall perform at least once per 

 calendar year a Method 9 at each listed combustion unit. 

 Readings shall be performed by a Certified Visible 

 Emission Evaluator. The results of each observation shall 

 be recorded in a bound log book or other format acceptable

 to the Department, kept at a designated office for at 

 least five years, and made available to NYSDEC 

 representatives upon request. Additional opacity readings 

 may be required by the Department.

Parameter Monitored: OPACITY

Upper Permit Limit: 20 percent

Reference Test Method: 40CFR 60 Appendix A Method 9

Monitoring Frequency: MINIMUM - ONCE PER CALENDAR YEAR

Averaging Method: 6-MINUTE AVERAGE (METHOD 9)

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 7/30/2012.

Subsequent reports are due every 6 calendar month(s).

Condition 29: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 227-1.3 (a)

Item 29.1:

The Compliance Certification activity will be performed for the Facility.

Item 29.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: MONITORING OF PROCESS OR CONTROL 

 DEVICE PARAMETERS AS SURROGATE
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 33 FINAL

Monitoring Description: 

 Visible emissions at the facility are limited to 20 

 percent opacity , except for one six minute period per 

 hour not to exceed 27 percent, based upon the six minute 

 average as stated in Reference Method 9 Appendix A 

 40CFR60. This condition applies to emission units 4 thru 

 19. Owner or operator shall perform at least once per 

 calendar year a Method 9 at each listed combustion unit. 

 Readings shall be performed by a Certified Visible 

 Emission Evaluator. The results of each observation shall 

 be recorded in a bound log book or other format acceptable

 to the Department, kept at a designated office for at 

 least five years, and made available to NYSDEC 

 representatives upon request. Additional opacity readings 

 may be required by the Department.

Parameter Monitored: OPACITY

Upper Permit Limit: 20 percent

Reference Test Method: 40CFR 60 Appendix A Method 9

Monitoring Frequency: MINIMUM - ONCE PER CALENDAR YEAR

Averaging Method: 6-MINUTE AVERAGE (METHOD 9)

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 7/30/2011.

Subsequent reports are due every 6 calendar month(s).

Condition 30: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 227-1.3 (a)

Item 30.1:

The Compliance Certification activity will be performed for the Facility.

Item 30.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: MONITORING OF PROCESS OR CONTROL 

 DEVICE PARAMETERS AS SURROGATE

Monitoring Description: 

Parameter Monitored: OPACITY

Upper Permit Limit: 20 percent

Monitoring Frequency: CONTINUOUS

Averaging Method: 6-MINUTE AVERAGE (METHOD 9)

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2012.

Subsequent reports are due every 12 calendar month(s).

Condition 1-7: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 34 FINAL

 Applicable Federal Requirement:6 NYCRR Subpart 227-2

Item 1-7.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 0NY210-00-0 OXIDES OF NITROGEN

Item 1-7.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 NOx RACT compliance is on a system-wide basis for all 

 KeySpan owned and/or operated affected facilities. The NOx

 RACT Plan has been approved by the NYSDEC.

Reference Test Method: 40CFR60 APP B

Monitoring Frequency: CONTINUOUS

Averaging Method: 24-HOUR AVERAGE

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2012.

Subsequent reports are due every 3 calendar month(s).

Condition 31: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR Subpart 227-2

Item 31.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 0NY210-00-0 OXIDES OF NITROGEN

Item 31.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 NOx RACT compliance is on a system-wide basis for all 

 KeySpan owned and/or operated affected facilities. The NOx

 RACT Plan has been approved by the NYSDEC.

Reference Test Method: 40CFR60 APP B

Monitoring Frequency: CONTINUOUS

Averaging Method: 24-HOUR AVERAGE

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2011.
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 35 FINAL

Subsequent reports are due every 3 calendar month(s).

Condition 1-8: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 227.2 (b) (1)

Item 1-8.1:

The Compliance Certification activity will be performed for the facility:

The Compliance Certification applies to:

 Emission Unit: U-00001

 Emission Unit: U-00002

 Emission Unit: U-00003

 Emission Unit: U-00004

 Emission Unit: U-00005

 Emission Unit: U-00006

 Emission Unit: U-00007

 Emission Unit: U-00008

 Emission Unit: U-00009

 Emission Unit: U-00010

 Emission Unit: U-00011

 Emission Unit: U-00012

 Emission Unit: U-00013

 Emission Unit: U-00014

 Emission Unit: U-00015

 Emission Unit: U-00016

 Emission Unit: U-00017

 Emission Unit: U-00018

 Emission Unit: U-00019

 Emission Unit: U-000S4

 Emission Unit: U-000S8
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 36 FINAL

 Regulated Contaminant(s):

 CAS No: 0NY075-00-0 PARTICULATES

Item 1-8.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: INTERMITTENT EMISSION TESTING

Monitoring Description: 

 Particulate emission limit for stationary combustion 

 installation units firing oil: The owner or operator shall

 complete the following once per term of this 

 permit:

 1-Submit to the Department an acceptable protocol for the 

 testing of particulate matter emission to demonstrate 

 compliance with the established limit in this 

 condition.

 2-Perform a stack test, based upon the approved 

 protocol.

 3-Submit to the Deparment a stack test report for 

 approval.

Parameter Monitored: PARTICULATES

Upper Permit Limit: 0.10 pounds per million Btus

Reference Test Method: 40CFR60 Method 5

Monitoring Frequency: ONCE DURING THE TERM OF THE PERMIT

Averaging Method: AVERAGING METHOD AS PER REFERENCE TEST

 METHOD INDICATED

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 7/30/2012.

Subsequent reports are due every 6 calendar month(s).

Condition 32: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 227.2 (b) (1)

Item 32.1:

The Compliance Certification activity will be performed for the facility:

The Compliance Certification applies to:

 Emission Unit: U-00001

 Emission Unit: U-00002

 Emission Unit: U-00003
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 37 FINAL

 Emission Unit: U-00004

 Emission Unit: U-00005

 Emission Unit: U-00006

 Emission Unit: U-00007

 Emission Unit: U-00008

 Emission Unit: U-00009

 Emission Unit: U-00010

 Emission Unit: U-00011

 Emission Unit: U-00012

 Emission Unit: U-00013

 Emission Unit: U-00014

 Emission Unit: U-00015

 Emission Unit: U-00016

 Emission Unit: U-00017

 Emission Unit: U-00018

 Emission Unit: U-00019

 Emission Unit: U-000S4

 Emission Unit: U-000S8

 Regulated Contaminant(s):

 CAS No: 0NY075-00-0 PARTICULATES

Item 32.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: INTERMITTENT EMISSION TESTING

Monitoring Description: 

 Particulate emission limit for stationary combustion 

 installation units firing oil: The owner or operator shall

 complete the following once per term of this 

 permit:

 1-Submit to the Department an acceptable protocol for the 

 testing of particulate matter emission to demonstrate 

 compliance with the established limit in this 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 38 FINAL

 condition.

 2-Perform a stack test, based upon the approved 

 protocol.

 3-Submit to the Deparment a stack test report for 

 approval.

Parameter Monitored: PARTICULATES

Upper Permit Limit: 0.10 pounds per million Btus

Reference Test Method: 40CFR60 Method 5

Monitoring Frequency: ONCE DURING THE TERM OF THE PERMIT

Averaging Method: AVERAGING METHOD AS PER REFERENCE TEST

 METHOD INDICATED

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 7/30/2011.

Subsequent reports are due every 6 calendar month(s).

Condition 33: Permit Requirements

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 243-1.6 (a)

Item 33.1:

The CAIR designated representative of each CAIR NOx Ozone Season source shall:

(i) submit to the department a complete CAIR permit application under section 243-3.3 in

accordance with the deadlines specified in section 243-3.2; and

(ii) submit in a timely manner any supplemental information that the department determines is

necessary in order to review a CAIR permit application and issue or deny a CAIR permit.

The owners and operators of each CAIR NOx Ozone Season source shall have a CAIR permit

issued by the department under Subpart 243-3 for the source and operate the source and the unit

in compliance with such CAIR permit.

Condition 34: Monitoring requirements

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 243-1.6 (b)

Item 34.1:

The emissions measurements recorded and reported in accordance with Subpart 243-8 shall be

used to determine compliance by each CAIR NOx Ozone Season source with the CAIR NOx

Ozone Season emissions limitation under subdivision (c) of this section.

Condition 35: NOx Ozone Season Emission Requirements

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 243-1.6 (c)

Item 35.1:
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 39 FINAL

As of the allowance transfer deadline for a control period, the owners and operators of each

CAIR NOx Ozone Season source and each CAIR NOx Ozone Season unit at the source shall

hold, in the source's compliance account, CAIR NOx Ozone Season allowances available for

compliance deductions for the control period under section 243-6.5(a) in an amount not less than

the tons of total nitrogen oxides emissions for the control period from all CAIR NOx Ozone

Season units at the source, as determined in accordance with Subpart 243-8. The CAIR NOx

ozone season is the period beginning May 1 of a calendar year, except as provided in section

243-1.6(c)(2), and ending on September 30 of the same year, inclusive.

A CAIR NOx Ozone Season unit shall be subject to the requirements under paragraph (c)(1) of

this section for the control period starting on the later of May 1, 2009 or the deadline for meeting

the unit's monitor certification requirements under sections 243-8.1(b)(1), (2), (3), or (7) and for

each control period thereafter.

A CAIR NOx Ozone Season allowance shall not be deducted, for compliance with the

requirements under paragraph (c)(1) of this section, for a control period in a calendar year before

the year for which the CAIR NOx Ozone Season allowance was allocated.

CAIR NOx Ozone Season allowances shall be held in, deducted from, or transferred into or

among CAIR NOx Ozone Season Allowance Tracking System accounts in accordance with

Subparts 243-6, 243-7, and 243-9.

A CAIR NOx Ozone Season allowance is a limited authorization to emit one ton of nitrogen

oxides in accordance with the CAIR NOx Ozone Season Trading Program. No provision of the

CAIR NOx Ozone Season Trading Program, the CAIR permit application, the CAIR permit, or

an exemption under section 243-1.5 and no provision of law shall be construed to limit the

authority of the State or the United States to terminate or limit such authorization.

A CAIR NOx Ozone Season allowance does not constitute a property right.

Upon recordation by the Administrator under Subpart 243-6, 243-7, or 243-9, every allocation,

transfer, or deduction of a CAIR NOx Ozone Season allowance to or from a CAIR NOx Ozone

Season source's compliance account is incorporated automatically in any CAIR permit of the

source.

Condition 36: Excess emission requirements

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 243-1.6 (d)

Item 36.1:

If a CAIR NOx Ozone Season source emits nitrogen oxides during any control period in excess

of the CAIR NOx Ozone Season emissions limitation, then:

(1) the owners and operators of the source and each CAIR NOx Ozone Season unit at the source

shall surrender the CAIR NOx Ozone Season allowances required for deduction under section

243-6.5(d)(1) and pay any fine, penalty, or assessment or comply with any other remedy

imposed, for the same violations, under the Act or applicable State law; and

(2) each ton of such excess emissions and each day of such control period shall constitute a

separate violation of this Subpart, the Act, and applicable State law.
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 40 FINAL

Condition 37: Recordkeeping and reporting requirements

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 243-1.6 (e)

Item 37.1:

Unless otherwise provided, the owners and operators of the CAIR NOx Ozone Season source

and each CAIR NOx Ozone Season unit at the source shall keep on site at the source each of the

following documents for a period of five years from the date the document is created. This

period may be extended for cause, at any time before the end of five years, in writing by the

department or the Administrator.

(i) The certificate of representation under section 243-2.4 for the CAIR designated

representative for the source and each CAIR NOx Ozone Season unit at the source and all

documents that demonstrate the truth of the statements in the certificate of representation;

provided that the certificate and documents shall be retained on site at the source beyond such

five-year period until such documents are superseded because of the submission of a new

certificate of representation under section 243-2.4 changing the CAIR designated representative.

(ii) All emissions monitoring information, in accordance with Subpart 243-8, provided that to the

extent that Subpart 243-8 provides for a three-year period for recordkeeping, the three-year

period shall apply.

(iii) Copies of all reports, compliance certifications, and other submissions and all records made

or required under the CAIR NOx Ozone Season Trading Program.

(iv) Copies of all documents used to complete a CAIR permit application and any other

submission under the CAIR NOx Ozone Season Trading Program or to demonstrate compliance

with the requirements of the CAIR NOx Ozone Season Trading Program.

Condition 38: Authorization and responsibilities of CAIR designated 

 representative

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 243-2.1

Item 38.1:

Except as provided under section 243-2.2, each CAIR NOx Ozone Season source, including all

CAIR NOx Ozone Season units at the source, shall have one and only one CAIR designated

representative, with regard to all matters under the CAIR NOx Ozone Season Trading Program

concerning the source or any CAIR NOx Ozone Season unit at the source.

The CAIR designated representative of the CAIR NOx Ozone Season source shall be selected by

an agreement binding on the owners and operators of the source and all CAIR NOx Ozone

Season units at the source and shall act in accordance with the certification statement in section

243-2.4(a)(4)(iv).

Upon receipt by the Administrator of a complete certificate of representation under section

243-2.4, the CAIR designated representative of the source shall represent and, by his or her

representations, actions, inactions, or submissions, legally bind each owner and operator of the

CAIR NOx Ozone Season source represented and each CAIR NOx Ozone Season unit at the
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 41 FINAL

source in all matters pertaining to the CAIR NOx Ozone Season Trading Program,

notwithstanding any agreement between the CAIR designated representative and such owners

and operators. The owners and operators shall be bound by any decision or order issued to the

CAIR designated representative by the department, the Administrator, or a court regarding the

source or unit.

No CAIR permit will be issued, no emissions data reports will be accepted, and no CAIR NOx

Ozone Season Allowance Tracking System account will be established for a CAIR NOx Ozone

Season unit at a source, until the Administrator has received a complete certificate of

representation under section 243-2.4 for a CAIR designated representative of the source and the

CAIR NOx Ozone Season units at the source.

 Each submission under the CAIR NOx Ozone Season Trading Program shall be submitted,

signed, and certified by the CAIR designated representative for each CAIR NOx Ozone Season

source on behalf of which the submission is made. Each such submission shall include the

following certification statement by the CAIR designated representative: "I am authorized to

make this submission on behalf of the owners and operators of the source or units for which the

submission is made. I certify under penalty of law that I have personally examined, and am

familiar with, the statements and information submitted in this document and all its attachments.

Based on my inquiry of those individuals with primary responsibility for obtaining the

information, I certify that the statements and information are to the best of my knowledge and

belief true, accurate, and complete. I am aware that there are significant penalties for submitting

false statements and information or omitting required statements and information, including the

possibility of fine or imprisonment."

Condition 39: Certificate of representation

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 243-2.4

Item 39.1:

Unless otherwise required by the department or the Administrator, documents of agreement

referred to in the certificate of representation shall not be submitted to the department or the

Administrator. Neither the department nor the Administrator shall be under any obligation to

review or evaluate the sufficiency of such documents, if submitted.

Condition 40: General requirements

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 243-8.1

Item 40.1:

The owners and operators, and to the extent applicable, the CAIR designated representative, of a

CAIR NOx Ozone Season unit, shall comply with the monitoring, recordkeeping, and reporting

requirements as provided in this Subpart and in Subpart H of 40 CFR Part 75. For purposes of

complying with such requirements, the definitions in section 243-1.2 and in 40 CFR 72.2 shall

apply, and the terms "affected unit," "designated representative," and "continuous emission

monitoring system" (or "CEMS") in 40 CFR Part 75 shall be deemed to refer to the terms "CAIR

NOx Ozone Season unit," "CAIR designated representative," and "continuous emission

monitoring system" (or "CEMS") respectively, as defined in section 243-1.2. The owner or

operator of a unit that is not a CAIR NOx Ozone Season unit but that is monitored under 40 CFR

75.72(b)(2)(ii) shall comply with the same monitoring, recordkeeping, and reporting
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 42 FINAL

requirements as a CAIR NOx Ozone Season unit.

'Requirements for installation, certification, and data accounting.' The owner or operator of each

CAIR NOx Ozone Season unit shall:

(1) install all monitoring systems required under this Subpart for monitoring NOx mass

emissions and individual unit heat input (including all systems required to monitor NOx

emission rate, NOx concentration, stack gas moisture content, stack gas flow rate, CO2 or O2

concentration, and fuel flow rate, as applicable, in accordance with 40 CFR 75.71 and 40 CFR

75.72);

(2) successfully complete all certification tests required under section 243-8.2 and meet all other

requirements of this Subpart and 40 CFR Part 75 applicable to the monitoring systems under

paragraph (a)(1) of this section; and

(3) record, report, and quality-assure the data from the monitoring systems under paragraph

(a)(1) of this section.

Condition 41: Prohibitions

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 243-8.1

Item 41.1:

No owner or operator of a CAIR NOx Ozone Season unit shall use any alternative monitoring

system, alternative reference method, or any other alternative to any requirement of this Subpart

without having obtained prior written approval in accordance with section 243-8.6.

No owner or operator of a CAIR NOx Ozone Season unit shall operate the unit so as to

discharge, or allow to be discharged, NOx emissions to the atmosphere without accounting for

all such emissions in accordance with the applicable provisions of this Subpart and 40 CFR Part

75.

No owner or operator of a CAIR NOx Ozone Season unit shall disrupt the continuous emission

monitoring system, any portion thereof, or any other approved emission monitoring method, and

thereby avoid monitoring and recording NOx mass emissions discharged into the atmosphere or

heat input, except for periods of recertification or periods when calibration, quality assurance

testing, or maintenance is performed in accordance with the applicable provisions of this Subpart

and 40 CFR Part 75.

No owner or operator of a CAIR NOx Ozone Season unit shall retire or permanently discontinue

use of the continuous emission monitoring system, any component thereof, or any other

approved monitoring system under this Subpart, except under any one of the following

circumstances:

(i) during the period that the unit is covered by an exemption under section 243-1.5 that is in

effect;

(ii) the owner or operator is monitoring emissions from the unit with another certified monitoring

system approved, in accordance with the applicable provisions of this Subpart and 40 CFR Part

75, by the department for use at that unit that provides emission data for the same pollutant or

parameter as the retired or discontinued monitoring system; or

(iii) the CAIR designated representative submits notification of the date of certification testing of

a replacement monitoring system for the retired or discontinued monitoring system in
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 43 FINAL

accordance with section 243-8.2(d)(3)(i).

Condition 42: Quarterly reports

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 243-8.5 (d)

Item 42.1:

The CAIR designated representative shall submit quarterly reports, as follows:

If the CAIR NOx Ozone Season unit is subject to an Acid Rain emissions limitation or a CAIR

NOx emissions limitation or if the owner or operator of such unit chooses to report on an annual

basis under this Subpart, the CAIR designated representative shall meet the requirements of

Subpart H of 40 CFR Part 75 (concerning monitoring of NOx mass emissions) for such unit for

the entire year and shall report the NOx mass emissions data and heat input data for such unit, in

an electronic quarterly report in a format prescribed by the Administrator, for each calendar

quarter beginning with:

(i) for a unit that commences commercial operation before July 1, 2007, the calendar quarter

covering May 1, 2008 through June 30, 2008;

(ii) for a unit that commences commercial operation on or after July 1, 2007, the calendar

quarter corresponding to the earlier of the date of provisional certification or the applicable

deadline for initial certification under section 243-8.1(b), unless that quarter is the third or fourth

quarter of 2007 or the first quarter of 2008, in which case reporting shall commence in the

quarter covering May 1, 2008 through June 30, 2008.

The CAIR designated representative shall submit each quarterly report to the Administrator

within 30 days following the end of the calendar quarter covered by the report. Quarterly reports

shall be submitted in the manner specified in 40 CFR 75.73(f).

For CAIR NOx Ozone Season units that are also subject to an Acid Rain emissions limitation or

the CAIR NOx Annual Trading Program, CAIR SO2 Trading Program, or the Mercury

Reduction Program for Coal-Fired Electric Utility Steam Generating Units (6 NYCRR Part 246),

quarterly reports shall include the applicable data and information required by Subparts F

through I of 40 CFR Part 75 as applicable, in addition to the NOx mass emission data, heat input

data, and other information required by this Subpart.

Condition 43: Compliance certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 243-8.5 (e)

Item 43.1:

The CAIR designated representative shall submit to the Administrator a compliance certification

(in a format prescribed by the Administrator) in support of each quarterly report based on

reasonable inquiry of those persons with primary responsibility for ensuring that all of the unit's

emissions are correctly and fully monitored. The certification shall state that:

(1) the monitoring data submitted were recorded in accordance with the applicable requirements

of this Subpart and 40 CFR Part 75, including the quality assurance procedures and

specifications;
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 44 FINAL

(2) for a unit with add-on NOx emission controls and for all hours where NOx data are

substituted in accordance with 40 CFR 75.34(a)(1), the add-on emission controls were operating

within the range of parameters listed in the quality assurance/quality control program under

appendix B to 40 CFR Part 75 and the substitute data values do not systematically underestimate

NOx emissions; and

(3) for a unit that is reporting on a control period basis under subparagraph (d)(2)(ii) of this

section, the NOx emission rate and NOx concentration values substituted for missing data under

Subpart D of 40 CFR Part 75 are calculated using only values from a control period and do not

systematically underestimate NOx emissions.

Condition 44: CAIR NOx Annual Trading Program General Conditions

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR Subpart 244-1

Item 44.1:

1) As of midnight of March 1, or midnight of the first business day thereafter if March 1 is not a

business day, the owners and operators shall hold, in their compliance account, Clean Air

Interstate Rule (CAIR) NOx allowances available for compliance deductions for the previous

control period (January 1 through December 31), in an amount not less than the total tons of

nitrogen oxides emissions from all CAIR NOx units at the source during that control period. A

CAIR NOx allowance shall not be deducted for a control period in a calendar year before the

year for which the CAIR NOx allowance was allocated. [244-1.6(c)(1), 244-1.2(b)(5),

244-1.2(b)(36), 244-1.6(c)(3)]

2) The owners and operators shall hold in their compliance account, CAIR NOx allowances

available for compliance deductions for the control period starting on the later of January 1,

2009 or the deadline for meeting a CAIR NOx unit's monitor certification requirements under

section 244-8.1(b)(1), (2), or (5) and for each control period thereafter. [244-1.6(c)(2)]

3) If a CAIR NOx source emits nitrogen oxides during any control period in excess of the CAIR

NOx emissions limitation, the owners and operators of the CAIR NOx source shall surrender

the CAIR NOx allowances required for deduction under 6NYCRR Part 244-6.5(d)(1) and pay

any fine, penalty, or assessment or comply with any other remedy imposed, for the same

violations, under the Act or applicable State law. Each ton of such excess emissions and each

day of such control period shall constitute a separate violation of this permit, the Act, and

applicable State law. [(244-1.6(d)]

4) Unless otherwise provided, the owners and operators of the CAIR NOx source shall keep on

site each of the following documents for a period of five years from the date the document is

created. This period may be extended for cause, at any time before the end of five years, in

writing by the department or the Administrator: [244-1.6(e)]

 (i) The certificate of representation under 6NYCRR Part 244-2.4 for the CAIR designated

representative for the source and all documents that demonstrate the truth of the statements in the

certificate of representation; provided that the certificate and documents shall be retained on site

at the source beyond such five year period until such documents are superseded because of the

submission of a new certificate of representation under 6NYCRR Part 244-2.4 changing the

CAIR designated representative.

 (ii) All emissions monitoring information, in accordance with 6NYCRR Part 244-8, provided

that to the extent that 6NYCRR Part 244-8 provides for a three year period for recordkeeping,
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 45 FINAL

the three year period shall apply.

 (iii) Copies of all reports, compliance certifications, and other submissions and all records

made or required under the CAIR NOx Annual Trading Program.

 (iv) Copies of all documents used to complete a CAIR permit application and any other

submission under the CAIR NOx Annual Trading Program or to demonstrate compliance with

the requirements of the CAIR NOx Annual Trading Program.

Condition 45: Designated CAIR Representative

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR Subpart 244-2

Item 45.1:

1) Each Clean Air Interstate Rule (CAIR) NOx source shall have one CAIR designated

representative and may have one alternate representative, as per 6NYCRR Part 244-2.2, with

regard to all matters under the CAIR NOx Annual Trading Program. The CAIR designated

representative shall be selected by an agreement binding on the owners and operators of the

source and act in accordance with the certification statement in 6NYCRR Part 244-2.4(a)(4)(iv). 

Upon receipt by the Administrator of a complete certificate of representation under 6NYCRR

Part 244-2.4, the CAIR designated representative of the source shall represent and, by his or her

representations, actions, inactions, or submissions, legally bind each owner and operator of the

CAIR NOx source represented in all matters pertaining to the CAIR NOx Annual Trading

Program, notwithstanding any agreement between the CAIR designated representative and such

owners and operators. The owners and operators shall be bound by any decision or order issued

to the CAIR designated representative by the department, the Administrator, or a court regarding

the source. [244-2.1(a), (b) & (c)] 

(2) Each submission under the CAIR NOx Annual Trading Program shall be submitted, signed,

and certified by the CAIR designated representative for each CAIR NOx source on behalf of

which the submission is made. Each such submission shall include the following certification

statement by the CAIR designated representative: "I am authorized to make this submission on

behalf of the owners and operators of the source or units for which the submission is made. I

certify under penalty of law that I have personally examined, and am familiar with, the

statements and information submitted in this document and all its attachments. Based on my

inquiry of those individuals with primary responsibility for obtaining the information, I certify

that the statements and information are to the best of my knowledge and belief true, accurate,

and complete. I am aware that there are significant penalties for submitting false statements and

information or omitting required statements and information, including the possibility of fine or

imprisonment." [244-2.1(e)]

Condition 46: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR Subpart 244-8

Item 46.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 0NY210-00-0 OXIDES OF NITROGEN

Item 46.2:
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 46 FINAL

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Monitoring and Reporting NOX emissions

 (1) The owners and operators, and to the extent 

 applicable, the CAIR designated representative shall 

 comply with all recordkeeping and reporting requirements 

 in this condition, the applicable recordkeeping and 

 reporting requirements under 40 CFR 75, and the 

 requirements of 6NYCRR Part 244-2.1(e)(1). 

 (2) The CAIR designated representative shall submit 

 quarterly reports of the the NOx mass emissions data and 

 heat input data for each CAIR NOx unit, in an electronic 

 quarterly report in a format prescribed by the 

 Administrator, for each calendar quarter beginning with 

 the calendar quarter corresponding to the earlier of the 

 date of provisional certification or the applicable 

 deadline for initial certification under 6NYCRR Part 

 244-8.1(b), unless that quarter is the third or fourth 

 quarter of 2007, in which case reporting shall commence in

 the quarter covering January 1, 2008 through March 31, 

 2008.

 (3) The CAIR designated representative shall submit each 

 quarterly report to the Administrator within 30 days 

 following the end of the calendar quarter covered by the 

 report. Quarterly reports shall be submitted in the manner

 specified in 40 CFR 75.73(f).

 (4) For CAIR NOx units that are also subject to an Acid 

 Rain emissions limitation or the CAIR NOx Ozone Season 

 Trading Program, CAIR SO2 Trading Program, or the Mercury 

 Reduction Program for Coal-Fired Electric Utility Steam 

 Generating Units (6NYCRR Part 246), quarterly reports 

 shall include the applicable data and information required

 by Subparts F through I of 40 CFR Part 75 as applicable, 

 in addition to the NOx mass emission data, heat input 

 data, and other information required by this 

 Subpart.

 (5) 'Compliance certification.' The CAIR designated 

 representative shall submit to the Administrator a 

 compliance certification (in a format prescribed by the 

 Administrator) in support of each quarterly report based 

 on reasonable inquiry of those persons with primary 

 responsibility for ensuring that all of the unit's 

 emissions are correctly and fully monitored. The 

 certification shall state that:
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 47 FINAL

 (i) the monitoring data submitted were recorded in 

 accordance with the applicable requirements of 6NYCRR Part

 244 and 40 CFR Part 75, including the quality assurance 

 procedures and specifications; and

 (ii) for a unit with add-on NOx emission controls and for 

 all hours where NOx data are substituted in accordance 

 with 40 CFR 75.34(a)(1), the add-on emission controls were

 operating within the range of parameters listed in the 

 quality assurance/quality control program under appendix B

 to 40 CFR Part 75 and the substitute data values do not 

 systematically underestimate NOx emissions.

 (6) Whenever any monitoring system fails to meet the 

 quality-assurance and quality-control requirements or data

 validation requirements of 40 CFR part 75, data shall be 

 substituted using the applicable missing data procedures 

 in Subpart D or Subpart H of, or appendix D or appendix E 

 to 40 CFR part 75. [ 244-8.3(a) ]

 (7) Whenever the owner or operator makes a replacement, 

 modification, or change in any certified continuous 

 emission monitoring system under 6NYCRR Part 244-8.1(a)(1)

 that may significantly affect the ability of the system to

 accurately measure or record NOx mass emissions or heat 

 input rate or to meet the quality-assurance and 

 quality-control requirements of 40 CFR 75.21 or appendix B

 to 40 CFR Part 75, the owner or operator shall recertify 

 the monitoring system in accordance with 40 CFR 75.20(b) .

 Furthermore, whenever the owner or operator makes a 

 replacement, modification, or change to the flue gas 

 handling system or the unit's operation that may 

 significantly change the stack flow or concentration 

 profile, the owner or operator shall recertify each 

 continuous emission monitoring system whose accuracy is 

 potentially affected by the change, in accordance with 40 

 CFR 75.20(b). Examples of changes to a continuous emission

 monitoring system that require recertification include 

 replacement of the analyzer, complete replacement of an 

 existing continuous emission monitoring system, or change 

 in location or orientation of the sampling probe or site. 

 Any fuel flowmeter system, and any excepted NOx monitoring

 system under appendix E to 40 CFR part 75, under 6NYCRR 

 Part 244-8.1(a)(1) are subject to the recertification 

 requirements in 40 CFR 75.20(g)(6). [224-8.2(d)(2)

 

Monitoring Frequency: CONTINUOUS

Averaging Method: ANNUAL TOTAL

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 48 FINAL

The initial report is due 4/30/2011.

Subsequent reports are due every 3 calendar month(s).

Condition 47: CAIR SO2 Trading Program General Provisions

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR Subpart 245-1

Item 47.1:

1) As of midnight of March 1, or midnight of the first business day thereafter (if March 1 is not

a business day) for a control period, the owners and operators of each Clean Air Interstate Rule

(CAIR) SO2 source shall hold, in the source's compliance account, a tonnage equivalent in

CAIR SO2 allowances available for compliance deductions for the control period (January 1

through December 31) not less than the tons of total sulfur dioxide emissions for the control

period from all CAIR SO2 units at the source. A CAIR SO2 allowance shall not be deducted,

for compliance with the requirements under paragraph (2) of this section, for a control period in

a calendar year before the year for which the CAIR SO2 allowance was allocated. 

[(245-1.2(b)(5), 245-1.6(c)(1), 245-1.2(b)(36), 245-1.6(c)(3)]

2) The owners and operators shall hold in their compliance account, CAIR SO2 allowances

available for compliance deductions for the control period starting on the later of January 1,

2010 or the deadline for meeting a CAIR SO2 unit's monitor certification requirements under

section 245-8.1(b)(1), (2), or (5) and for each control period thereafter. [245-1.6(c)(2)]

3) If a CAIR SO2 source emits sulfur dioxide during any control period in excess of the CAIR

SO2 emissions limitation, the owners and operators of the source shall surrender the CAIR SO2

allowances required for deduction under 6NYCRR Part 245-6.5(d)(1) and pay any fine, penalty,

or assessment or comply with any other remedy imposed, for the same violations, under the Act

or applicable State law. Each ton of such excess emissions and each day of such control period

shall constitute a separate violation of this Subpart, the Act, and applicable State law.

[(245-1.6(d)]

4) Unless otherwise provided, the owners and operators of the CAIR SO2 source shall keep on

site at the source each of the following documents for a period of five years from the date the

document is created. This period may be extended for cause, at any time before the end of five

years, in writing by the department or the Administrator: [245-1.6(e)]

 (i) The certificate of representation under 6NYCRR Part 245-2.4 for the CAIR designated

representative for the source and all documents that demonstrate the truth of the statements in the

certificate of representation; provided that the certificate and documents shall be retained on site

at the source beyond such five-year period until such documents are superseded because of the

submission of a new certificate of representation under 6NYCRR Part 245-2.4 changing the

CAIR designated representative.

 (ii) All emissions monitoring information, in accordance with 6NYCRR Part 245-8, provided

that to the extent that 6NYCRR Part 245-8 provides for a three-year period for recordkeeping,

the three-year period shall apply.

 (iii) Copies of all reports, compliance certifications, and other submissions and all records

made or required under the CAIR SO2 Trading Program.

 (iv) Copies of all documents used to complete a CAIR permit application and any other

submission under the CAIR SO2 Trading Program or to demonstrate compliance with the

requirements of the CAIR SO2 Trading Program.

Condition 48: Designated CAIR Representative
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 49 FINAL

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR Subpart 245-2

Item 48.1:

1) Each CAIR SO2 source shall have one and only one CAIR designated representative and

may have one alternate representative, as per 6NYCRR Part 245-2.2, with regard to all matters

under the CAIR SO2 Trading Program. The CAIR designated representative of the CAIR SO2

source shall be selected by an agreement binding on the owners and operators of the source and

all CAIR SO2 units at the source and shall act in accordance with the certification statement in

6NYCRR Part 245-2.4(a)(4)(iv). Upon receipt by the Administrator of a complete certificate of

representation under 6NYCRR Part 245-2.4, the CAIR designated representative of the source

shall represent and, by his or her representations, actions, inactions, or submissions, legally bind

each owner and operator of the CAIR SO2 source represented and each CAIR SO2 unit at the

source in all matters pertaining to the CAIR SO2 Trading Program, notwithstanding any

agreement between the CAIR designated representative and such owners and operators. The

owners and operators shall be bound by any decision or order issued to the CAIR designated

representative by the department, the Administrator, or a court regarding the source or unit.

[245-2.1(a), (b) & (c)]

(2) Each submission under the CAIR SO2 Trading Program shall be submitted, signed, and

certified by the CAIR designated representative for each CAIR SO2 source on behalf of which

the submission is made. Each such submission shall include the following certification statement

by the CAIR designated representative: "I am authorized to make this submission on behalf of

the owners and operators of the source or units for which the submission is made. I certify under

penalty of law that I have personally examined, and am familiar with, the statements and

information submitted in this document and all its attachments. Based on my inquiry of those

individuals with primary responsibility for obtaining the information, I certify that the statements

and information are to the best of my knowledge and belief true, accurate, and complete. I am

aware that there are significant penalties for submitting false statements and information or

omitting required statements and information, including the possibility of fine or imprisonment." 

[245-2.1(e)]

Condition 49: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR Subpart 245-8

Item 49.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 007446-09-5 SULFUR DIOXIDE

Item 49.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Monitoring and Reporting SO2 emissions:

 1) The owners and operators, and to the extent applicable,
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 50 FINAL

 the Clean Air Interstate Rule (CAIR) designated 

 representative, of a CAIR SO2 unit, shall comply with the 

 monitoring, recordkeeping, and reporting requirements as 

 provided in Subpart 6 NYCRR Part 245-8 and in 40 CFR Part 

 75, Subparts F and G. For purposes of complying with such

 requirements, the definitions in section 245-1.2 and 40 

 CFR 72.2 shall apply, and the terms "affected unit," 

 "designated representative," and "continuous emission 

 monitoring system" (or "CEMS") in 40 CFR Part 75 shall be 

 deemed to refer to the terms "CAIR SO2 unit," "CAIR 

 designated representative," and "continuous emission 

 monitoring system" (or "CEMS") respectively, as defined in

 section 245-1.2. The owner or operator of a unit that is 

 not a CAIR SO2 unit but that is monitored under 40 CFR 

 75.16(b)(2) shall comply with the same monitoring, 

 recordkeeping, and reporting requirements as a CAIR SO2 

 unit. [245-8.1]

 2)The owner or operator of each CAIR SO2 unit shall: 

 [245-8.1(a)]

 (i) install all monitoring systems required under this

 Subpart for monitoring SO2 mass emissions and individual 

 unit heat input (including all systems required to monitor

 SO2 concentration, stack gas moisture content, stack gas 

 flow rate, CO2 or O2 concentration, and fuel flow rate, as

 applicable, in accordance with 40 CFR 75.11 and 40 CFR 

 75.16);

 (ii) successfully complete all certification tests 

 required under Part 245-8.2 and meet all other 

 requirements of this section and 40 CFR Part 75 applicable

 to the monitoring systems under this section; and

 (iii) record, report, and quality-assure the data from

 the monitoring systems under paragraph of this 

 section.

 3) The owner or operator shall meet the monitoring system

 certification and other requirements of section 

 245-8.1(a)(1) and (2) on or before the following dates. 

 The owner or operator shall record, report, and 

 quality-assure the data from the monitoring systems under 

 section 245-8.1(a)(1) on and after the following dates. 

 [245-8.1(b)]

 (i) For the CAIR SO2 unit that commences commercial 

 operation before July 1, 2008, by January 1, 2009.

 (ii) For the CAIR SO2 unit that commences commercial 

 operation on or after July 1, 2008, by the later of the 

 following dates: January 1, 2009; or 90 unit operating 

 days or 180 calendar days, whichever occurs first, after 

 the date on which the unit commences commercial 

 operation.

 4) Whenever the owner or operator makes a replacement, 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 51 FINAL

 modification, or change in any certified continuous 

 emission monitoring system under section 245-8.1(a)(1) 

 that may significantly affect the ability of the system to

 accurately measure or record SO2 mass emissions or heat 

 input rate or to meet the quality-assurance and 

 quality-control requirements of 40 CFR 75.21 or appendix B

 to 40 CFR Part 75, the owner or operator shall recertify 

 the monitoring system in accordance with 40 CFR 75.20(b). 

 Furthermore, whenever the owner or operator makes a 

 replacement, modification, or change to the flue gas 

 handling system or the unit's operation that may 

 significantly change the stack flow or concentration 

 profile, the owner or operator shall recertify each 

 continuous emission monitoring system whose accuracy is 

 potentially affected by the change, in accordance with 40 

 CFR 75.20(b). Examples of changes to a continuous emission

 monitoring system that require recertification include: 

 replacement of the analyzer, complete replacement of an 

 existing continuous emission monitoring system, or change 

 in location or orientation of the sampling probe or site. 

 Any fuel flowmeter system under section 245-8.1(a)(1) is 

 subject to the recertification requirements in 40 CFR 

 75.20(g)(6). [245-8.2(d)(2)]

 5) Whenever any monitoring system fails to meet the 

 quality-assurance and quality-control requirements or data

 validation requirements of 40 CFR Part 75, data shall be 

 substituted using the applicable missing data procedures 

 in Subpart D of or appendix D to 40 CFR Part 75. 

 [245-8.3(a)]

 6) The CAIR designated representative shall comply with 

 all recordkeeping and reporting requirements in section 

 245-8.3, the applicable recordkeeping and reporting 

 requirements in Subparts F and G of 40 CFR Part 75, and 

 the requirements of section 245-2.1(e)(1). 

 [245-8.5(a)]

 7) The owner or operator of a CAIR SO2 unit shall comply 

 with requirements of 40 CFR 75.62 for monitoring plans. 

 [245-8.5(b)]

 8) The CAIR designated representative shall submit an 

 application to the department within 45 days after 

 completing all initial certification or recertification 

 tests required under section 245-8.2, including the 

 information required under 40 CFR 75.63. [245-8.5(c) 

 ]

 9) The CAIR designated representative shall submit 

 quarterly reports of the SO2 mass emissions data and heat 

 input data for each CAIR SO2 unit, in an electronic 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 52 FINAL

 quarterly report in a format prescribed by the 

 Administrator, for each calendar quarter beginning with: 

 [245-8.5(d)(1)]

 i) the calendar quarter covering January 1, 2009 

 through March 31, 2009 for a unit that commences 

 commercial operation before July 1, 2008; or

 ii) for a unit that commences commercial operation on 

 or after July 1, 2008, the calendar quarter corresponding 

 to the earlier of the date of provisional certification or

 the applicable deadline for initial certification under 

 section 245-8.1(b), unless that quarter is the third or 

 fourth quarter of 2008, in which case reporting shall 

 commence in the quarter covering January 1, 2009 through 

 March 31, 2009.

 10) The CAIR designated representative shall submit each 

 quarterly report to the Administrator within 30 days 

 following the end of the calendar quarter covered by the 

 report. Quarterly reports shall be submitted in the manner

 specified in 40 CFR 75.64. [245-8.5(d)(2)]

 11) For CAIR SO2 units that are also subject to an Acid 

 Rain emissions limitation or the CAIR NOX Annual Trading 

 Program, CAIR NOX Ozone Season Trading Program, or the 

 Mercury Reduction Program for Coal-Fired Electric Utility 

 Steam Generating Units (6 NYCRR Part 246), quarterly 

 reports shall include the applicable data and information 

 required by Subparts F through I of 40 CFR Part 75 as 

 applicable, in addition to the SO2 mass emission data, 

 heat input data, and other information required by this 

 Subpart. [245-8.5(d)(3)]

 12) The CAIR designated representative shall submit to 

 the Administrator a compliance certification (in a format 

 prescribed by the Administrator) in support of each 

 quarterly report based on reasonable inquiry of those 

 persons with primary responsibility for ensuring that all 

 of the unit's emissions are correctly and fully monitored.

 The certification shall state that: [245-8.5(e)]

 i) the monitoring data submitted were recorded in 

 accordance with the applicable requirements of this 

 Subpart and 40 CFR Part 75, including the quality 

 assurance procedures and specifications; and

 ii) for a unit with add-on SO2 emission controls and 

 for all hours where SO2 data are substituted in accordance

 with 40 CFR 75.34(a)(1), the add-on emission controls were

 operating within the range of parameters listed in the 

 quality assurance/quality control program under appendix B

 to 40 CFR Part 75 and the substitute data values do not 

 systematically underestimate SO2 emissions.

Monitoring Frequency: CONTINUOUS
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 53 FINAL

Averaging Method: ANNUAL TOTAL

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2011.

Subsequent reports are due every 3 calendar month(s).

Condition 1-9: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 249.3 (d)

Item 1-9.1:

The Compliance Certification activity will be performed for the Facility.

Item 1-9.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Control equipment or other emission reduction methods 

 approved by the department as BART must be installed and 

 operating no later than January 1, 2014.

Monitoring Frequency: SINGLE OCCURRENCE

Reporting Requirements: ONCE / BATCH OR MONITORING OCCURRENCE

Condition 50: Facility Subject to Title IV Acid Rain Regulations and 

 Permitting

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:40 CFR Part 72

Item 50.1: This facility is subject to the Title IV Acid Rain Regulations found in 40 CFR

Parts 72, 73, 75, 76, 77 and 78. The Acid Rain Permit is an attachment to this permit.

 ** ** Emission Unit Level  

Condition 51: Emission Point Definition By Emission Unit

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR Subpart 201-6

Item 51.1(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00001

 Emission Point: 00001 

 Height (ft.): 250 Diameter (in.): 192

 NYTMN (km.): 4496.994 NYTME (km.): 614.398 Building: BOILERBLD1
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 54 FINAL

Item 51.2(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00002

 Emission Point: 00002 

 Height (ft.): 350 Diameter (in.): 123

 NYTMN (km.): 4496.99 NYTME (km.): 614.448 Building: BOILERBLD2

Item 51.3(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00003

 Emission Point: 00003 

 Height (ft.): 25 Diameter (in.): 32

 NYTMN (km.): 4497.11 NYTME (km.): 614.355 Building: HOUSEBOILE

Item 51.4(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00004

 Emission Point: 00004 

 Height (ft.): 52 Diameter (in.): 119

 NYTMN (km.): 4497.056 NYTME (km.): 614.336 Building: CT#1

Item 51.5(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00005

 Emission Point: 00005 

 Height (ft.): 52 Diameter (in.): 119

 NYTMN (km.): 4497.058 NYTME (km.): 614.349 Building: CT#2

Item 51.6(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00006

 Emission Point: 00006 

 Height (ft.): 52 Diameter (in.): 119

 NYTMN (km.): 4497.05 NYTME (km.): 614.337 Building: CT#3

Item 51.7(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00007

 Emission Point: 00007 

 Height (ft.): 52 Diameter (in.): 119
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 55 FINAL

 NYTMN (km.): 4497.051 NYTME (km.): 614.351 Building: CT#4

Item 51.8(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00008

 Emission Point: 00008 

 Height (ft.): 52 Diameter (in.): 119

 NYTMN (km.): 4497.046 NYTME (km.): 614.337 Building: CT#5

Item 51.9(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00009

 Emission Point: 00009 

 Height (ft.): 52 Diameter (in.): 119

 NYTMN (km.): 4497.047 NYTME (km.): 614.344 Building: CT#6

Item 51.10(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00010

 Emission Point: 00010 

 Height (ft.): 52 Diameter (in.): 119

 NYTMN (km.): 4497.047 NYTME (km.): 614.351 Building: CT#7

Item 51.11(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00011

 Emission Point: 00011 

 Height (ft.): 52 Diameter (in.): 119

 NYTMN (km.): 4497.039 NYTME (km.): 614.338 Building: CT#8

Item 51.12(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00012

 Emission Point: 00012 

 Height (ft.): 36 Diameter (in.): 91

 NYTMN (km.): 4497.039 NYTME (km.): 614.346 Building: CT#9

Item 51.13(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00013
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 56 FINAL

 Emission Point: 00013 

 Height (ft.): 36 Diameter (in.): 91

 NYTMN (km.): 4497.038 NYTME (km.): 614.354 Building: CT#9

Item 51.14(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00014

 Emission Point: 00014 

 Height (ft.): 36 Diameter (in.): 91

 NYTMN (km.): 4497.031 NYTME (km.): 614.34 Building: CT#10

Item 51.15(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00015

 Emission Point: 00015 

 Height (ft.): 36 Diameter (in.): 91

 NYTMN (km.): 4497.032 NYTME (km.): 614.347 Building: CT#10

Item 51.16(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00016

 Emission Point: 00016 

 Height (ft.): 36 Diameter (in.): 91

 NYTMN (km.): 4497.033 NYTME (km.): 614.354 Building: CT#11

Item 51.17(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00017

 Emission Point: 00017 

 Height (ft.): 36 Diameter (in.): 91

 NYTMN (km.): 4497.025 NYTME (km.): 614.34 Building: CT#11

Item 51.18(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00018

 Emission Point: 00018 

 Height (ft.): 36 Diameter (in.): 91

 NYTMN (km.): 4497.026 NYTME (km.): 614.348 Building: CT#12

Item 51.19(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 57 FINAL

 Emission Unit: U-00019

 Emission Point: 00019 

 Height (ft.): 36 Diameter (in.): 91

 NYTMN (km.): 4497.027 NYTME (km.): 614.356 Building: CT#12

Item 51.20(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-000S4

 Emission Point: 000S4 

 Height (ft.): 40 Diameter (in.): 3

 NYTMN (km.): 4497.019 NYTME (km.): 614.34 Building: CT#1

Item 51.21(From Mod 1):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-000S8

 Emission Point: 000S8 

 Height (ft.): 40 Diameter (in.): 3

 NYTMN (km.): 4497.021 NYTME (km.): 614.35 Building: CT#5

Condition 52: Process Definition By Emission Unit

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR Subpart 201-6

Item 52.1(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00001

 Process: P01 Source Classification Code: 1-01-004-04

 Process Description: 

 This process is the combustion of #6 residual oil in a 

 tangentially fired steam electric boiler. In order to 

 improve boiler operation, a fuel additive may be mixed 

 into the residual oil prior to combustion.

 Emission Source/Control: ES001 - Combustion 

 Design Capacity: 1,825 million Btu per hour

Item 52.2(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00001

 Process: P02 Source Classification Code: 1-01-005-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 tangentially fired steam electric boiler.
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 58 FINAL

 Emission Source/Control: ES001 - Combustion 

 Design Capacity: 1,825 million Btu per hour

Item 52.3(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00001

 Process: P03 Source Classification Code: 1-01-005-01

 Process Description: 

 This process is the combustion of #2 oil in a 

 tangentially fired steam ectric boiler.

 Emission Source/Control: ES001 - Combustion 

 Design Capacity: 1,825 million Btu per hour

Item 52.4(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00001

 Process: P04 Source Classification Code: 1-01-006-04

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a tangentially fired steam electric boiler.

 Emission Source/Control: ES001 - Combustion 

 Design Capacity: 1,825 million Btu per hour

Item 52.5(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00001

 Process: P05 Source Classification Code: 1-01-013-02

 Process Description: 

 This process is the co-firing of waste fuel in a 

 tangentially fired steam electric boiler.This fuel is 

 fired in combination with a primary fuel, at a rate not to

 exceed 5%. Waste oil includes gas main drip water and gas 

 transmission condensate. Waste fuel is tested for 

 compliance with 6NYCRR Part 225-2.3 and co-fired with 

 primary boiler fuel at a maximum rate equivalent to 5% of 

 the total heat input into the boiler. Lead, PCB's, and 

 total halogens are tested on every delivery from off site.

 ( only Nationalgrid waste fuel is accepted ). Monthly 

 samples are collected and analyzed from each waste fuel 

 tank on site. Analysis for sulfur and heat content have 

 been waived by the NYSDEC since the co-firing rate 

 restrictions insures that the "as burned" waste fuel in 

 the boiler is always within the limitations of Part 

 225-2.3. Lead, PCB's and halogens limitations are complied

 with on an "as delivered" and/or "as generated" basis.

 Emission Source/Control: ES001 - Combustion 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 59 FINAL

 Design Capacity: 1,825 million Btu per hour

Item 52.6(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00001

 Process: P06 Source Classification Code: 1-01-013-02

 Process Description: 

 This process is the incineration, by co-firing with a 

 primary fuel, of a non-hazardous boiler chemical cleaning 

 solution. Following a chemical cleaning of the water-side 

 of the boilers tubes with an acidic solution, the spent 

 material is evaporated when the boiler is operating at 

 nominal full load. The spent chemical cleanup solution may

 be from any company owned boiler.

 Emission Source/Control: ES001 - Combustion 

 Design Capacity: 1,825 million Btu per hour

Item 52.7(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00002

 Process: P07 Source Classification Code: 1-01-004-04

 Process Description: 

 This process is the combustion of #6 residual oil in a 

 tangentially fired steam electric boiler. In order to 

 improve boiler operation, a fuel additive may be mixed 

 into the residual oil prior to combustion.

 Emission Source/Control: ES002 - Combustion 

 Design Capacity: 1,825 million Btu per hour

Item 52.8(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00002

 Process: P08 Source Classification Code: 1-01-005-01

 Process Description: 

 This process is the combustion of #1 residual oil in a 

 tangentially fired steam electric boiler. In order to 

 improve boiler operation, a fuel additive may be mixed 

 into the residual oil prior to combustion.

 Emission Source/Control: ES002 - Combustion 

 Design Capacity: 1,825 million Btu per hour

Item 52.9(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00002

 Process: P09 Source Classification Code: 1-01-005-01
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 60 FINAL

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 tangentially fired steam electric boiler. When natural gas

 is unavailable, this fuel is used during the initial 

 startup of the boiler

 Emission Source/Control: ES002 - Combustion 

 Design Capacity: 1,825 million Btu per hour

Item 52.10(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00002

 Process: P10 Source Classification Code: 1-01-006-04

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a tangentially fired steam electric boiler

 Emission Source/Control: ES002 - Combustion 

 Design Capacity: 1,825 million Btu per hour

Item 52.11(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00002

 Process: P11 Source Classification Code: 1-01-013-02

 Process Description: 

 This process is the co-firing of waste fuel in a 

 tangentially fired steam electric boiler.This fuel is 

 fired in combination with a primary fuel, at a rate not to

 exceed 5%. Waste oil includes gas main drip water and gas 

 transmission condensate. Waste fuel is tested for 

 compliance with 6NYCRR Part 225-2.3 and co-fired with 

 primary boiler fuel at a maximum rate equivalent to 5% of 

 the total heat input into the boiler. Lead, PCB's, and 

 total halogens are tested on every delivery from off site.

 ( only Nationalgrid waste fuel is accepted ). Monthly 

 samples are collected and analyzed from each waste fuel 

 tank on site. Analysis for sulfur and heat content have 

 been waived by the NYSDEC since the co-firing rate 

 restrictions insures that the "as burned" waste fuel in 

 the boiler is always within the limitations of Part 

 225-2.3. Lead, PCB's and halogens limitations are complied

 with on an "as delivered" and/or "as generated" basis.

 Emission Source/Control: ES002 - Combustion 

 Design Capacity: 1,825 million Btu per hour

Item 52.12(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00002
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 61 FINAL

 Process: P12 Source Classification Code: 1-01-013-02

 Process Description: 

 This process is the incineration, by co-firing with a 

 primary fuel, of a non-hazardous boiler chemical cleaning 

 solution. Following a chemical cleaning of the water-side 

 of the boilers tubes with an acidic solution, the spent 

 material is evaporated when the boiler is operating at 

 nominal full load. The spent chemical cleanup solution may

 be from any company owned boiler.

 Emission Source/Control: ES002 - Combustion 

 Design Capacity: 1,825 million Btu per hour

Item 52.13(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00003

 Process: P25 Source Classification Code: 1-02-005-01

 Process Description: 

 This process involves the combustion of #1 distillate oil

 in an industrial steam boiler.

 Emission Source/Control: ES003 - Combustion 

 Design Capacity: 39 million Btu per hour

Item 52.14(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00003

 Process: P26 Source Classification Code: 1-02-005-01

 Process Description: 

 This process involves the combustion of #2 distillate oil

 in an industrial steam boiler.

 Emission Source/Control: ES003 - Combustion 

 Design Capacity: 39 million Btu per hour

Item 52.15(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00003

 Process: P27 Source Classification Code: 1-02-006-02

 Process Description: 

 This process involves the combustion of natural gas in an

 industrial steam boiler.

 Emission Source/Control: ES003 - Combustion 

 Design Capacity: 39 million Btu per hour

Item 52.16(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 62 FINAL

 Emission Unit: U-00004

 Process: P28 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES004 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.17(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00004

 Process: P29 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES004 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.18(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00004

 Process: P30 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a combustion turbine.

 Emission Source/Control: ES004 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.19(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00005

 Process: P31 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 63 FINAL

 fouling.

 Emission Source/Control: ES005 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.20(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00005

 Process: P32 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES005 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.21(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00005

 Process: P33 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a combustion turbine.

 Emission Source/Control: ES005 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.22(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00006

 Process: P34 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES006 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.23(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 64 FINAL

 Emission Unit: U-00006

 Process: P35 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES006 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.24(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00006

 Process: P36 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a combustion turbine.

 Emission Source/Control: ES006 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.25(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00007

 Process: P37 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES007 - Combustion 

 Design Capacity: 276 million Btu per hour

Item 52.26(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00007

 Process: P38 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 65 FINAL

 fouling.

 Emission Source/Control: ES007 - Combustion 

 Design Capacity: 276 million Btu per hour

Item 52.27(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00007

 Process: P39 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a combustion turbine.

 Emission Source/Control: ES007 - Combustion 

 Design Capacity: 276 million Btu per hour

Item 52.28(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00008

 Process: P40 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES008 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.29(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00008

 Process: P41 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES008 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.30(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 66 FINAL

 Emission Unit: U-00008

 Process: P42 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a combustion turbine.

 Emission Source/Control: ES008 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.31(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00009

 Process: P43 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES009 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.32(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00009

 Process: P44 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES009 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.33(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00009

 Process: P45 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a combustion turbine.

 Emission Source/Control: ES009 - Combustion 

 Design Capacity: 322 million Btu per hour
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 67 FINAL

Item 52.34(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00010

 Process: P46 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES010 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.35(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00010

 Process: P47 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES010 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.36(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00010

 Process: P48 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a combustion turbine.

 Emission Source/Control: ES010 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.37(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00011

 Process: P49 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 68 FINAL

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES011 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.38(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00011

 Process: P50 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES011 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.39(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00011

 Process: P51 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a combustion turbine.

 Emission Source/Control: ES011 - Combustion 

 Design Capacity: 322 million Btu per hour

Item 52.40(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00012

 Process: P52 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES012 - Combustion 

 Design Capacity: 334 million Btu per hour
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 69 FINAL

Item 52.41(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00012

 Process: P53 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES012 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.42(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00012

 Process: P54 Source Classification Code: 2-01-002-01

 Process Description: 

 This is the combustion of pipeline natural gas in a 

 combustion turbine.

 Emission Source/Control: ES012 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.43(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00013

 Process: P55 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES013 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.44(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00013

 Process: P56 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 70 FINAL

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES013 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.45(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00013

 Process: P57 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas on

 a combustion turbine.

 Emission Source/Control: ES013 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.46(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00014

 Process: P58 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES014 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.47(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00014

 Process: P59 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES014 - Combustion 

 Design Capacity: 334 million Btu per hour
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 71 FINAL

Item 52.48(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00014

 Process: P60 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a combustion turbine.

 Emission Source/Control: ES014 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.49(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00015

 Process: P61 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES015 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.50(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00015

 Process: P62 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES015 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.51(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00015

 Process: P63 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas in
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 72 FINAL

 a combustion turbine.

 Emission Source/Control: ES015 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.52(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00016

 Process: P64 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES016 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.53(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00016

 Process: P65 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES016 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.54(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00016

 Process: P66 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a combustion turbine.

 Emission Source/Control: ES016 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.55(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 73 FINAL

 Emission Unit: U-00017

 Process: P67 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES017 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.56(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00017

 Process: P68 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES017 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.57(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00017

 Process: P69 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a combustion turbine.

 Emission Source/Control: ES017 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.58(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00018

 Process: P70 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 74 FINAL

 fouling.

 Emission Source/Control: ES018 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.59(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00018

 Process: P71 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES018 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.60(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00018

 Process: P72 Source Classification Code: 2-01-002-01

 Process Description: 

 This is the combustion of pipeline natural gas in a 

 combustion turbine.

 Emission Source/Control: ES018 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.61(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00019

 Process: P73 Source Classification Code: 2-01-009-01

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES019 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.62(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 75 FINAL

 Emission Unit: U-00019

 Process: P74 Source Classification Code: 2-01-001-01

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 combustion turbine. In order to improve combustion a fuel 

 additive may be mixed with the distillate oil prior to 

 combustion. In addition, when fuel oil is stored for 

 extended periods, a biocide may be added to prevent 

 fouling.

 Emission Source/Control: ES019 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.63(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00019

 Process: P75 Source Classification Code: 2-01-002-01

 Process Description: 

 This process is the combustion of pipeline natural gas in

 a combustion turbine.

 Emission Source/Control: ES019 - Combustion 

 Design Capacity: 334 million Btu per hour

Item 52.64(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-000S4

 Process: P91 Source Classification Code: 2-02-009-02

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 diesel engine. This engine is used to start the associated

 combustion turbine. During each startup the engine 

 operates for less than 15 minutes

 Emission Source/Control: ES0S4 - Combustion 

 Design Capacity: 340 horsepower (mechanical)

Item 52.65(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-000S4

 Process: P92 Source Classification Code: 2-01-001-02

 Process Description: 

 This process is the combustion of #2 distillate oil in a 

 diesel engine. This engine is used to start the associated

 combustion turbine. During each startup the engine 

 operates for less than 15 minutes

 Emission Source/Control: ES0S4 - Combustion 

 Design Capacity: 340 horsepower (mechanical)
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 76 FINAL

Item 52.66(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-000S8

 Process: P93 Source Classification Code: 2-02-009-02

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 diesel engine. This engine is used to start the associated

 combustion turbine. During each startup the engine 

 operates for less than 15 minutes

 Emission Source/Control: ES0S8 - Combustion 

 Design Capacity: 340 horsepower (mechanical)

Item 52.67(From Mod 1):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-000S8

 Process: P94 Source Classification Code: 2-01-001-02

 Process Description: 

 This process is the combustion of #1 distillate oil in a 

 diesel engine. This engine is used to start the associated

 combustion turbine. During each startup the engine 

 operates for less than 15 minutes

 Emission Source/Control: ES0S8 - Combustion 

 Design Capacity: 340 horsepower (mechanical)

Condition 1-10: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 249.3 (f)

Item 1-10.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00001

Item 1-10.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 The emission limits in this permit for NOx, SO2, and/or 

 PM10 established under Part 249 are based on New York's 

 Best Available Retrofit Technology (BART) Rule (6 NYCRR 

 Part 249), are effective on the date of this permit's 

 issuance, and are state-enforceable. Federal 

 enforceability of these facility-specific requirements is 

 effective on the date on which these emission limits, as 

 submitted to EPA as a revision to New York State's 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 77 FINAL

 Implementation Plan for Regional Haze, are published in 

 the Federal Register.

Monitoring Frequency: SEMI-ANNUALLY

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2012.

Subsequent reports are due every 3 calendar month(s).

Condition 1-11: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 227-1.3 (a)

Item 1-11.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00001 Emission Point: 00001

Item 1-11.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: MONITORING OF PROCESS OR CONTROL 

 DEVICE PARAMETERS AS SURROGATE

Monitoring Description: 

 Opacity is measured on a continuous opacity monitor as a 

 compliance indicator. Operation and reporting requirements

 apply when fuel oil is burned. According to Consent Order 

 No. D1-9000-97-08 Appendix A 8- quarterly reports: 

 quarterly opacity incident reports will be submitted to 

 the NYSDEC 60 days following the end of a calendar 

 quarter.

Manufacturer Name/Model Number: SICK OMD41

Parameter Monitored: OPACITY

Upper Permit Limit: 20.0 percent

Reference Test Method: 40 CFR 60 APP B

Monitoring Frequency: CONTINUOUS

Averaging Method: AVERAGING METHOD AS PER REFERENCE TEST

 METHOD INDICATED

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 60 days after the reporting period.

The initial report is due 5/30/2012.

Subsequent reports are due every 3 calendar month(s).

Condition 53: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 227-1.3 (a)

Item 53.1:

The Compliance Certification activity will be performed for:
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 78 FINAL

 Emission Unit: U-00001 Emission Point: 00001

Item 53.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: MONITORING OF PROCESS OR CONTROL 

 DEVICE PARAMETERS AS SURROGATE

Monitoring Description: 

 Opacity is measured on a continuous opacity monitor as a 

 compliance indicator. Operation and reporting requirements

 apply when fuel oil is burned. According to Consent Order 

 No. D1-9000-97-08 Appendix A 8- quarterly reports: 

 quarterly opacity incident reports will be submitted to 

 the NYSDEC 60 days following the end of a calendar 

 quarter.

Manufacturer Name/Model Number: SICK OMD41

Parameter Monitored: OPACITY

Upper Permit Limit: 20.0 percent

Reference Test Method: 40 CFR 60 APP B

Monitoring Frequency: CONTINUOUS

Averaging Method: AVERAGING METHOD AS PER REFERENCE TEST

 METHOD INDICATED

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 60 days after the reporting period.

The initial report is due 5/30/2011.

Subsequent reports are due every 3 calendar month(s).

Condition 1-12: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 249.3 (a)

Item 1-12.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00002

 Regulated Contaminant(s):

 CAS No: 0NY075-00-0 PARTICULATES

Item 1-12.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: INTERMITTENT EMISSION TESTING

Monitoring Description: 

 This Particulate limit is required to demonstrate 

 compliance with the EPA Haze Rule.

 Stack test is required once per term limit.

 Effective: 01/01/14.
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 79 FINAL

Upper Permit Limit: 0.10 pounds per million Btus

Reference Test Method: EPA Method 5

Monitoring Frequency: CONTINUOUS

Averaging Method: 1-HOUR AVERAGE

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2012.

Subsequent reports are due every 3 calendar month(s).

Condition 1-13: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 249.3 (a)

Item 1-13.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00002

 Regulated Contaminant(s):

 CAS No: 0NY210-00-0 OXIDES OF NITROGEN

Item 1-13.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: CONTINUOUS EMISSION MONITORING (CEM)

Monitoring Description: 

 This Nitrogen Oxides limit is required to demonstrate 

 compliance with the EPA Haze Rule.

 This limit applies when burning natural gas.

 Effective: 01/01/2014

Manufacturer Name/Model Number: TBD

Upper Permit Limit: 0.10 pounds per million Btus

Reference Test Method: Method 7

Monitoring Frequency: CONTINUOUS

Averaging Method: 24 HOUR DAILY AVERAGE (ARITHMETIC 

 MEAN)

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2012.

Subsequent reports are due every 3 calendar month(s).

Condition 1-14: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 249.3 (a)

Item 1-14.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00002
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 80 FINAL

 Regulated Contaminant(s):

 CAS No: 0NY210-00-0 OXIDES OF NITROGEN

Item 1-14.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: CONTINUOUS EMISSION MONITORING (CEM)

Monitoring Description: 

 This Nitrogen Oxides limit is required to demonstrate 

 compliance with the EPA Haze Rule.

 This limit applies when burnig oil.

 Effective date: 01/01/2014

Manufacturer Name/Model Number: TBD

Upper Permit Limit: 0.20 pounds per million Btus

Reference Test Method: Method 7

Monitoring Frequency: CONTINUOUS

Averaging Method: 24 HOUR DAILY AVERAGE (ARITHMETIC 

 MEAN)

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2012.

Subsequent reports are due every 3 calendar month(s).

Condition 1-15: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 249.3 (a)

Item 1-15.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00002

 Regulated Contaminant(s):

 CAS No: 007446-09-5 SULFUR DIOXIDE

Item 1-15.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: MONITORING OF PROCESS OR CONTROL 

 DEVICE PARAMETERS AS SURROGATE

Monitoring Description: 

 This Oil Sulfur Content limit is required to demonstrate 

 compliance with the EPA Haze Rule. This limit will be 

 assumed during any 24-hour averaging period in which oil 

 is fired.

 Effective: 01/01/14.

Work Practice Type: PARAMETER OF PROCESS MATERIAL

Parameter Monitored: SULFUR CONTENT
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 81 FINAL

Upper Permit Limit: 0.37 percent by weight

Reference Test Method: ASTM 4294

Monitoring Frequency: CONTINUOUS

Averaging Method: 24-HOUR AVERAGE

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2012.

Subsequent reports are due every 3 calendar month(s).

Condition 1-16: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 249.3 (f)

Item 1-16.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00002

Item 1-16.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 The emission limits in this permit for NOx, SO2, and/or 

 PM10 established under Part 249 are based on New York's 

 Best Available Retrofit Technology (BART) Rule (6 NYCRR 

 Part 249), are effective on the date of this permit's 

 issuance, and are state-enforceable. Federal 

 enforceability of these facility-specific requirements is 

 effective on the date on which these emission limits, as 

 submitted to EPA as a revision to New York State's 

 Implementation Plan for Regional Haze, are published in 

 the Federal Register.

Monitoring Frequency: SEMI-ANNUALLY

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2012.

Subsequent reports are due every 3 calendar month(s).

Condition 1-17: Compliance Certification

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 227-1.3 (a)

Item 1-17.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00002 Emission Point: 00002

Item 1-17.2:
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 82 FINAL

Compliance Certification shall include the following monitoring:

Monitoring Type: MONITORING OF PROCESS OR CONTROL 

 DEVICE PARAMETERS AS SURROGATE

Monitoring Description: 

 Opacity is measured on a continuous opacity monitor as a 

 compliance indicator. Operation and reporting requirements

 apply when fuel oil is burned. According to Consent Order 

 No. D1-9000-97-08 Appendix A 8- quarterly reports: 

 quarterly opacity incident reports will be submitted to 

 the NYSDEC 60 days following the end of a calendar 

 quarter.

Manufacturer Name/Model Number: SICK OMD41

Parameter Monitored: OPACITY

Upper Permit Limit: 20.0 percent

Reference Test Method: 40CFR60 APP B

Monitoring Frequency: CONTINUOUS

Averaging Method: AVERAGING METHOD AS PER REFERENCE TEST

 METHOD INDICATED

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 60 days after the reporting period.

The initial report is due 5/30/2012.

Subsequent reports are due every 3 calendar month(s).

Condition 54: Compliance Certification

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable Federal Requirement:6 NYCRR 227-1.3 (a)

Item 54.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00002 Emission Point: 00002

Item 54.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: MONITORING OF PROCESS OR CONTROL 

 DEVICE PARAMETERS AS SURROGATE

Monitoring Description: 

 Opacity is measured on a continuous opacity monitor as a 

 compliance indicator. Operation and reporting requirements

 apply when fuel oil is burned. According to Consent Order 

 No. D1-9000-97-08 Appendix A 8- quarterly reports: 

 quarterly opacity incident reports will be submitted to 

 the NYSDEC 60 days following the end of a calendar 

 quarter.

Manufacturer Name/Model Number: SICK OMD41

Parameter Monitored: OPACITY

Upper Permit Limit: 20.0 percent
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 83 FINAL

Reference Test Method: 40CFR60 APP B

Monitoring Frequency: CONTINUOUS

Averaging Method: AVERAGING METHOD AS PER REFERENCE TEST

 METHOD INDICATED

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 60 days after the reporting period.

The initial report is due 5/30/2011.

Subsequent reports are due every 3 calendar month(s).
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 84 FINAL

 STATE ONLY ENFORCEABLE CONDITIONS

 ** ** Facility Level  

 NOTIFICATION OF GENERAL PERMITTEE OBLIGATIONS

This section contains terms and conditions which are not federally enforceable. Permittees

may also have other obligations under regulations of general applicability

Item A: General Provisions for State Enforceable Permit Terms and

 Condition - 6 NYCRR Part 201-5

 Any person who owns and/or operates stationary sources 

 shall operate and maintain all emission units and any 

 required emission control devices in compliance with all 

 applicable Parts of this Chapter and existing laws, and 

 shall operate the facility in accordance with all 

 criteria, emission limits, terms, conditions, and 

 standards in this permit. Failure of such person to 

 properly operate and maintain the effectiveness of such 

 emission units and emission control devices may be 

 sufficient reason for the Department to revoke or deny a 

 permit.

 The owner or operator of the permitted facility must 

 maintain all required records on-site for a period of five

 years and make them available to representatives of the 

 Department upon request. Department representatives must 

 be granted access to any facility regulated by this 

 Subpart, during normal operating hours, for the purpose of

 determining compliance with this and any other state and 

 federal air pollution control requirements, regulations or

 law.

 STATE ONLY APPLICABLE REQUIREMENTS

The following conditions are state applicable requirements and are not subject to 

compliance certification requirements unless otherwise noted or required 

 under 6 NYCRR Part 201.

Condition 55: Contaminant List

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable State Requirement:ECL 19-0301

Item 55.1:

Emissions of the following contaminants are subject to contaminant specific requirements in this

permit(emission limits, control requirements or compliance monitoring conditions).

 CAS No: 000124-38-9

 Name: CARBON DIOXIDE
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 85 FINAL

 CAS No: 007446-09-5

 Name: SULFUR DIOXIDE

 CAS No: 0NY075-00-0

 Name: PARTICULATES

 CAS No: 0NY210-00-0

 Name: OXIDES OF NITROGEN

Condition 56: Unavoidable noncompliance and violations

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable State Requirement:6 NYCRR 201-1.4

Item 56.1:

At the discretion of the commissioner a violation of any applicable emission standard for

necessary scheduled equipment maintenance, start-up/shutdown conditions and malfunctions or

upsets may be excused if such violations are unavoidable. The following actions and

recordkeeping and reporting requirements must be adhered to in such circumstances.

(a) The facility owner and/or operator shall compile and maintain records of all

equipment maintenance or start-up/shutdown activities when they can be expected to result in an

exceedance of any applicable emission standard, and shall submit a report of such activities to

the commissioner's representative when requested to do so in writing or when so required by a

condition of a permit issued for the corresponding air contamination source except where

conditions elsewhere in this permit which contain more stringent reporting and notification

provisions for an applicable requirement, in which case they supercede those stated here. Such

reports shall describe why the violation was unavoidable and shall include the time, frequency

and duration of the maintenance and/or start-up/shutdown activities and the identification of air

contaminants, and the estimated emission rates. If a facility owner and/or operator is subject to

continuous stack monitoring and quarterly reporting requirements, he need not submit reports for

equipment maintenance or start-up/shutdown for the facility to the commissioner's

representative.

(b) In the event that emissions of air contaminants in excess of any emission standard

in 6 NYCRR Chapter III Subchapter A occur due to a malfunction, the facility owner and/or

operator shall report such malfunction by telephone to the commissioner's representative as soon

as possible during normal working hours, but in any event not later than two working days after

becoming aware that the malfunction occurred. Within 30 days thereafter, when requested in

writing by the commissioner's representative, the facility owner and/or operator shall submit a

written report to the commissioner's representative describing the malfunction, the corrective

action taken, identification of air contaminants, and an estimate of the emission rates. These

reporting requirements are superceded by conditions elsewhere in this permit which contain

reporting and notification provisions for applicable requirements more stringent than those

above.

(c) The Department may also require the owner and/or operator to include in reports

described under (a) and (b) above an estimate of the maximum ground level concentration of

each air contaminant emitted and the effect of such emissions depending on the deviation of the

malfunction and the air contaminants emitted.

(d) In the event of maintenance, start-up/shutdown or malfunction conditions which
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 86 FINAL

result in emissions exceeding any applicable emission standard, the facility owner and/or

operator shall take appropriate action to prevent emissions which will result in contravention of

any applicable ambient air quality standard. Reasonably available control technology, as

determined by the commissioner, shall be applied during any maintenance, start-up/shutdown or

malfunction condition subject to this paragraph.

(e) In order to have a violation of a federal regulation (such as a new source performance

standard or national emissions standard for hazardous air pollutants) excused, the specific

federal regulation must provide for an affirmative defense during start-up, shutdowns,

malfunctions or upsets.

Condition 57: Air pollution prohibited

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable State Requirement:6 NYCRR 211.2

Item 57.1:

No person shall cause or allow emissions of air contaminants to the outdoor atmosphere of such

quantity, characteristic or duration which are injurious to human, plant or animal life or to

property, or which unreasonably interfere with the comfortable enjoyment of life or property.

Notwithstanding the existence of specific air quality standards or emission limits, this

prohibition applies, but is not limited to, any particulate, fume, gas, mist, odor, smoke, vapor,

pollen, toxic or deleterious emission, either alone or in combination with others.

Condition 1-18: Visible Emissions Limited

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable State Requirement:6 NYCRR 211.2

Item 1-18.1:

Except as permitted by a specific part of this Subchapter and for open fires for which a restricted

burning permit has been issued, no person shall cause or allow any air contamination source to

emit any material having an opacity equal to or greater than 20 percent (six minute average)

except for one continuous six-minute period per hour of not more than 57 percent opacity.

Condition 1-19: Compliance Demonstration

 Effective between the dates of 03/27/2012 and 02/23/2016

 Applicable State Requirement:6 NYCRR 211.2

Item 1-19.1:

The Compliance Demonstration activity will be performed for the Facility.

Item 1-19.2:

Compliance Demonstration shall include the following monitoring:

Monitoring Type: MONITORING OF PROCESS OR CONTROL 

 DEVICE PARAMETERS AS SURROGATE

Monitoring Description: 

 Except as permitted by a specific part of Title 6 of the 

 NYCRR, no person shall cause or allow any air 

 contamination source to emit any material having an 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 87 FINAL

 opacity equal to or greater than 20 percent (six minute 

 average) except for one continuous six-minute period per 

 hour of not more than 57 percent opacity.

 Operators of air contamination sources that are not exempt

 from permitting and where a continuous opacity monitor is 

 not utilized for measuring smoke emissions, shall be 

 required to perform the following:

 1) Observe the stack(s) or vent(s) once per day for 

 visible emissions. This observation(s) must be conducted 

 during daylight hours except during adverse weather 

 conditions (fog, rain, or snow).

 2) The results of each observation must be recorded in a 

 bound logbook or other format acceptable to the 

 Department. The following data must be recorded for each 

 stack:

 - weather condition

 - was a plume observed?

 This logbook must be retained at the facility for five (5)

 years after the date of the last entry.

 3) If the operator observes any visible emissions (other 

 than steam - see below) two consecutive days, then a 

 Method 9 analysis (based upon a 6-minute mean) of the 

 affected emission point(s) must be conducted within two 

 (2) business days of such occurrence. The results of the 

 Method 9 analysis must be recorded in the logbook. The 

 operator must contact the Regional Air Pollution Control 

 Engineer within one (1) business day of performing the 

 Method 9 analysis if the opacity standard is contravened. 

 Upon notification, any corrective actions or future 

 compliance schedules shall be presented to the Department 

 for acceptance.

 **  NOTE ** Steam plumes generally form after leaving the 

 top of the stack (this is known as a detached plume). The

 distance between the stack and the beginning of the 

 detached plume may vary, however, there is (normally) a 

 distinctive distance between the plume and stack. Steam 

 plumes are white in color and have a billowy consistency. 

 Steam plumes dissipate within a short distance of the 

 stack (the colder the air the longer the steam plume will 

 last) and leave no dispersion trail downwind of the 

 stack.

Parameter Monitored: OPACITY

Upper Permit Limit: 20 percent

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 88 FINAL

 DESCRIPTION

Averaging Method: 6 MINUTE AVERAGE

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2012.

Subsequent reports are due every 3 calendar month(s).

Condition 77: Compliance Demonstration

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable State Requirement:6 NYCRR 242-1.4 (b)

Item 77.1:

The Compliance Demonstration activity will be performed for the Facility.

Item 77.2:

Compliance Demonstration shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 (1) Applicability. Notwithstanding Subdivision (a) of 

 this Section, any unit that, on or before December 1, 

 2008, applies for a enforceable permit condition 

 restricting the supply of the unit's annual electrical 

 output to the electric grid to less than or equal to 10 

 percent of the annual gross generation of the unit, and 

 that from and after January 1, 2009 complies with the 10 

 percent restriction and the provisions in Paragraph (b)(3)

 of this Section, shall be exempt from the requirements of 

 this Part, except for the provisions of this Section, 

 Sections 242-1.2, 242-1.3, and 242-1.6 of this 

 Part.

 (2) Effective date. The exemption under Paragraph (b)(1) 

 of this Section shall become effective as of January 1, 

 2009 and remain in effect unless and until the unit loses 

 its exemption under Subparagraph (b)(3)(v) of this 

 Section.

 (3) Compliance.

 (i) A unit exempt under Paragraph (b)(1) of this Section 

 shall comply with the restriction on percentage of annual 

 gross generation that may be supplied to the electric grid

 described in Paragraph (b)(1) of this Section.

 (ii) A unit exempt under Paragraph (b)(1) of this Section 

 shall report to the department the amount of annual gross 

 generation and the amount of annual gross generation 

 supplied to the electric grid during the year by the 

 following February 1st.
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 89 FINAL

 (iii) For a period of 10 years from the date the records 

 are created, the owners and operators of a unit exempt 

 under Paragraph (b)(1) of this Section shall retain, at 

 the source that includes the unit, records demonstrating 

 that the conditions of the permit under Paragraph (b)(1) 

 of this Section were met. The 10-year period for keeping 

 records may be extended for cause, at any time prior to 

 the end of the period, in writing by the department. The 

 owners and operators bear the burden of proof that the 

 unit met the restriction on the percentage of annual gross

 generation that may be supplied to the electric 

 grid.

 (iv) The owners and operators and, to the extent 

 applicable, the CO2 authorized account representative of a

 unit exempt under Paragraph (b)(1) of this Section shall 

 comply with all the requirements of this Part concerning 

 all time periods for which the exemption is not in effect,

 even if such requirements arise, or must be complied with,

 after the exemption takes effect.

 (v) On the earlier of the following dates, a unit exempt 

 under Paragraph (b)(1) of this Section shall lose its 

 exemption:

 (a) the date on which the restriction on the percentage of

 annual gross generation that may be supplied to the 

 electric grid described in Paragraph (b)(1) of this 

 Section is removed from the unit's permit or otherwise 

 becomes no longer applicable in any year that commences on

 or after January 1, 2009; or

 (b) the first date on which the unit fails to comply, or 

 on which the owners and operators fail to meet their 

 burden of proving that the unit is complying, with the 

 restriction on the percentage of annual gross generation 

 that may be supplied to the electric grid described in 

 Paragraph (b)(1) of this Section during any year that 

 commences on or after January 1, 2009.

 (vi) A unit that loses its exemption in accordance with 

 Subparagraph (b)(3)(v) of this Section shall be subject to

 the requirements of this Part. For the purpose of applying

 permitting requirements under Subpart 242-3 of this Part, 

 allocating allowances under Subpart 242-5 of this Part, 

 and applying monitoring requirements under Subpart 242-8 

 of this Part, the unit shall be treated as commencing 

 operation on the date the unit loses its exemption.

 (4) Reduction in CO2 Budget Trading Program base budget. 

 In the event that a unit applies for and receives a permit

 condition that renders the unit exempt under Subdivision 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 90 FINAL

 (b) of this Section, then the department shall reduce the 

 CO2 Budget Trading Program base budget to remove the 

 number of tons equal to the unit's average annual 

 emissions from the previous three calendar years.

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 7/30/2011.

Subsequent reports are due every 6 calendar month(s).

Condition 78: CO2 Budget Trading Program - Excess emission requirements

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable State Requirement:6 NYCRR 242-1.5

Item 78.1:

The owners and operators of a CO2 budget source that has excess emissions in any control

period shall:

(1) forfeit the CO2 allowances required for deduction under 6 NYCRR Part 242-6.5(d)(1),

provided CO2 offset allowances may not be used to cover any part of such excess emissions; and

(2) pay any fine, penalty, or assessment or comply with any other remedy imposed under 6

NYCRR Part 242-6.5(d)(2).

Condition 79: Compliance Demonstration

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable State Requirement:6 NYCRR Subpart 242-4

Item 79.1:

The Compliance Demonstration activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 000124-38-9 CARBON DIOXIDE

Item 79.2:

Compliance Demonstration shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Annual Compliance Certification Report:

 (a) For each control period in which a CO2 budget source 

 is subject to the CO2 requirements of subdivision 

 242-1.5(c) of this Part, CO2 authorized account 

 representative of the source shall submit to the 

 department by March 1st following the relevant control 

 period, a compliance certification report.

 (b) The compliance certification report shall include the 

 following elements:

 (1) identification of the source and each CO2 budget 

 unit at the source;
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 91 FINAL

 (2) as an option, the serial numbers of the CO2 

 allowances that are to be deducted from the source's 

 compliance account under section 242-6.5 of this Part for 

 the control period, including the serial numbers of any 

 CO2 offset allowances that are to be deducted subject to 

 the limitations of section 242-6.5(a)(3) of this Part; 

 and

 (3) the compliance certification under subdivision (c) 

 of this section (below).

 (c) In the compliance certification report the CO2 

 authorized account representative shall certify, based on 

 reasonable inquiry of those persons with primary 

 responsibility for operating the source and the CO2 budget

 units at the source in compliance with the CO2 Budget 

 Trading Program, whether the source and each CO2 budget 

 unit at the source for which the compliance certification 

 is submitted was operated during the calendar years 

 covered by the report in compliance with the requirements 

 of the CO2 Budget Trading Program, including:

 (1) whether the source was operated in compliance with 

 the CO2 requirements of section 242-1.5(c) of this Part;

 (2) whether the monitoring plan applicable to each unit

 at the source has been maintained to reflect the actual 

 operation and monitoring of the unit, and contains all 

 information necessary to attribute CO2 emissions to the 

 unit, in accordance with Subpart 242-8 of this Part;

 (3) whether all the CO2 emissions from the units at the

 source were monitored or accounted for through the missing

 data procedures and reported in the quarterly monitoring 

 reports, including whether conditional data were reported 

 in the quarterly reports in accordance with Subpart 242-8 

 of this Part. If conditional data were reported, the owner

 or operator shall indicate whether the status of all 

 conditional data has been resolved and all necessary 

 quarterly report resubmissions have been made;

 (4) whether the facts that form the basis for 

 certification under Subpart 242-8 of each monitor at each 

 unit at the source, or for using an excepted monitoring 

 method or alternative monitoring method approved under 

 Subpart 242-8 of this Part, if any, have changed; and

 (5) if a change is required to be reported under 

 paragraph (c)(4) above, specify the nature of the change, 

 the reason for the change, when the change occurred, and 

 how the unit's compliance status was determined subsequent

 to the change, including what method was used to determine

 emissions when a change mandated the need for monitor 

 recertification.

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: MARCH 1
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 92 FINAL

Condition 80: Compliance Demonstration

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable State Requirement:6 NYCRR Subpart 242-8

Item 80.1:

The Compliance Demonstration activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 000124-38-9 CARBON DIOXIDE

Item 80.2:

Compliance Demonstration shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Recordkeeping and Reporting (6NYCRR Part 242-8.5)

 (a) General provisions. The CO2 authorized account 

 representative shall comply with all recordkeeping and 

 reporting requirements in this section, the applicable 

 record keeping and reporting requirements under 40 CFR 

 75.73 and with the requirements of section 242-2.1(e) of 

 this Part.

 (b) Monitoring plans. The owner or operator of a CO2 

 budget unit shall submit a monitoring plan in the manner 

 prescribed in 40 CFR 75.62.

 (c) Certification applications. The CO2 authorized account

 representative shall submit an application to the 

 department within 45 days after completing all CO2 

 monitoring system initial certification or recertification

 tests required under section 242-8.2 of this Subpart 

 including the information required under 40 CFR 75.63 and 

 40 CFR 75.53(e) and (f).

 (d) Quarterly reports. The CO2 authorized account 

 representative shall submit quarterly reports, as 

 follows:

 (1) The CO2 authorized account representative shall 

 report the CO2 mass emissions data and heat input data for

 the CO2 budget unit, in an electronic format prescribed by

 the administrator unless otherwise prescribed by the 

 department for each calendar quarter.

 (2) The CO2 authorized account representative shall 

 submit each quarterly report to the department or its 

 agent within 30 days following the end of the calendar 

 quarter covered by the report. Quarterly reports shall be 

 submitted in the manner specified in subpart H of 40 CFR 

 part 75 and 40 CFR 75.64. Quarterly reports shall be 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 93 FINAL

 submitted for each CO2 budget unit (or group of units 

 using a common stack), and shall include all of the data 

 and information required in subpart G of 40 CFR part 75, 

 except for opacity, NOx, and SO2 provisions.

 (3) The CO2 authorized account representative shall 

 submit to the department or its agent a compliance 

 certification in support of each quarterly report based on

 reasonable inquiry of those persons with primary 

 responsibility for ensuring that all of the unit's 

 emissions are correctly and fully monitored. The 

 certification shall state that:

 (i) the monitoring data submitted were recorded in 

 accordance with the applicable requirements of this 

 Subpart and 40 CFR part 75, including the quality 

 assurance procedures and specifications;

 (ii) for a unit with add-on CO2 emissions controls 

 and for all hours where data are substituted in accordance

 with 40 CFR 75.34(a)(1), the add-on emissions controls 

 were operating within the range of parameters listed in 

 the quality assurance/quality control program under 

 appendix B of 40 CFR part 75 and the substitute values do 

 not systematically underestimate CO2 emissions; and

 (iii) the CO2 concentration values substituted for 

 missing data under Subpart D of 40 CFR part 75 do not 

 systematically underestimate CO2 emissions.

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2011.

Subsequent reports are due every 3 calendar month(s).

Condition 81: Compliance Demonstration

 Effective between the dates of 02/24/2011 and 02/23/2016

 Applicable State Requirement:6 NYCRR 242-8.5

Item 81.1:

The Compliance Demonstration activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 000124-38-9 CARBON DIOXIDE

Item 81.2:

Compliance Demonstration shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Recordkeeping and Reporting (6NYCRR Part 242-8.5)

 (a) General provisions. The CO2 authorized account 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 94 FINAL

 representative shall comply with all recordkeeping and 

 reporting requirements in this section, the applicable 

 record keeping and reporting requirements under 40 CFR 

 75.73 and with the requirements of section 242-2.1(e) of 

 this Part.

 (b) Monitoring plans. The owner or operator of a CO2 

 budget unit shall submit a monitoring plan in the manner 

 prescribed in 40 CFR 75.62.

 (c) Certification applications. The CO2 authorized account

 representative shall submit an application to the 

 department within 45 days after completing all CO2 

 monitoring system initial certification or recertification

 tests required under section 242-8.2 of this Subpart 

 including the information required under 40 CFR 75.63 and 

 40 CFR 75.53(e) and (f).

 (d) Quarterly reports. The CO2 authorized account 

 representative shall submit quarterly reports, as 

 follows:

 (1) The CO2 authorized account representative shall 

 report the CO2 mass emissions data and heat input data for

 the CO2 budget unit, in an electronic format prescribed by

 the administrator unless otherwise prescribed by the 

 department for each calendar quarter.

 (2) The CO2 authorized account representative shall 

 submit each quarterly report to the department or its 

 agent within 30 days following the end of the calendar 

 quarter covered by the report. Quarterly reports shall be 

 submitted in the manner specified in subpart H of 40 CFR 

 part 75 and 40 CFR 75.64. Quarterly reports shall be 

 submitted for each CO2 budget unit (or group of units 

 using a common stack), and shall include all of the data 

 and information required in subpart G of 40 CFR part 75, 

 except for opacity, NOx, and SO2 provisions.

 (3) The CO2 authorized account representative shall 

 submit to the department or its agent a compliance 

 certification in support of each quarterly report based on

 reasonable inquiry of those persons with primary 

 responsibility for ensuring that all of the unit's 

 emissions are correctly and fully monitored. The 

 certification shall state that:

 (i) the monitoring data submitted were recorded in 

 accordance with the applicable requirements of this 

 Subpart and 40 CFR part 75, including the quality 

 assurance procedures and specifications;

 (ii) for a unit with add-on CO2 emissions controls 

 and for all hours where data are substituted in accordance

 with 40 CFR 75.34(a)(1), the add-on emissions controls 

 were operating within the range of parameters listed in 

 the quality assurance/quality control program under 
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 95 FINAL

 appendix B of 40 CFR part 75 and the substitute values do 

 not systematically underestimate CO2 emissions; and

 (iii) the CO2 concentration values substituted for 

 missing data under Subpart D of 40 CFR part 75 do not 

 systematically underestimate CO2 emissions.

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2011.

Subsequent reports are due every 3 calendar month(s).
 

Permit ID: 1-2820-00553/00025 Facility DEC ID: 1282000553

 Air Pollution Control Permit Conditions

Renewal 2/Mod 1/Active Page 96 FINAL