### Instructionsfor Completing the Process Data Template

This template is to be used to record the 30 daily averages of specific process data required by the ICR. The ERT does not have the capability to store these daily averages. This spreadsheet included 4 separate surrogate worksheets,in case the boiler tested is tested for all surrogates at 4 different dates.This spreadsheet is intended to be used for one boiler of one facility.Data for multiple boilers should be handled by using separate copies of this spreadsheet. are required (if applicable to your boilers' operation). You do not need to populate cells shaded in gray, as they are automaticallypopulated from the Boiler Information worksheet. Please Do Not modify the structure of this spreadsheet by adding or subtracting rows, columns, cells. Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_Processdata.xls(example:8100_Unit_2_Processdata.xls).

Pleaserefer to the following steps when using these spreadsheets.

BoilerInformation Worksheet

Pleaseenter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Informationworksheet.

ProcessData Worksheets

Pleaseuse one process data worksheetfor each HAP surrogate even is simultaneous testing of different HAP surrogates was done.

### This template is to be used to record the 30 daily averages of specific process data required by the ICR. The ERT does not have the capability to store these daily averages. This spreadsheet included 4 separate surrogate worksheets,in case the This spreadsheet is intended to be used for one boiler of one facility.Data for multiple boilers should be handled by using separate copies of this spreadsheet. Fields shaded in yellow are required (if applicable to your boilers' operation). You do not need to populate cells shaded in gray, as they are Please Do Not modify the structure of this spreadsheet by Please name each resulting spreadsheet with the following naming convention:

Pleaseenter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Informationworksheet.

Pleaseuse one process data worksheetfor each HAP surrogate even is simultaneous testing of different HAP surrogates wasEIA

Facility Code Facility Name Boiler ID

6288 Healy 1EIA

Facility Code Facility Name Boiler ID

6288 Healy 1

Daily A verage Process Data for a 30 Day Period Including the Testing Date Date Coal Firing Rate Coal Firing Rate (units) Day 1 5/1/2010 off-lin (outage) Day 2 5/2/2010 off-lin (outage) Day 3 5/3/2010 off-lin (outage) Day 4 5/4/2010 off-lin (outage) Day 5 5/5/2010 off-lin (outage) Day 6 5/6/2010 off-lin (outage) Day 7 5/7/2010 off-lin (outage) Day 8 5/8/2010 49,178 lb/hr Day 9 5/9/2010 51,514 lb/hr Day 10 5/10/2010 51,350 lb/hr Day 11 5/11/2010 54,907 lb/hr Day 12 5/12/2010 13,579 lb/hr Day 13 5/13/2010 50,412 lb/hr Day 14 5/14/2010 53,792 lb/hr Day 15 5/15/2010 52,076 lb/hr Day 16 5/16/2010 53,037 lb/hr Day 17 5/17/2010 52,770 lb/hr Day 18 5/18/2010 51,932 lb/hr Day 19 5/19/2010 51,365 lb/hr Day 20 5/20/2010 50,748 lb/hr Day 21 5/21/2010 50,731 lb/hr Day 22 5/22/2010 48,316 lb/hr Day 23 5/23/2010 49,432 lb/hr Day 24 5/24/2010 50,161 lb/hr Day 25 5/25/2010 49,485 lb/hr Day 26 5/26/2010 50,348 lb/hr Day 27 5/27/2010 50,926 lb/hr Day 28 5/28/2010 51,554 lb/hr Day 29 5/29/2010 49,951 lb/hr Day 30 5/30/2010 50,116 lb/hr Day 31 5/31/2010 49,052 lb/hrDaily A verage Process Data for a 30 Day Period Including the Testing Date Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr)

358.4 222.7 351.1 245.8 355.0 245.8 371.4 245.8 102.7 60.4 349.2 246.0 372.2 246.0 356.5 246.1 354.9 246.0 348.5 245.9 348.3 246.1 356.8 246.0 351.2 246.1 356.0 246.1 342.9 246.1 348.7 246.0 355.3 246.0 343.6 232.3 354.3 245.9 350.8 246.1 351.7 246.0 351.7 246.0 347.3 246.0 349.2 245.9Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe)

23.7 26.0 25.7 27.8 25.7 28.4 25.8 28.2 8.0 9.1 25.8 28.3 25.7 28.1 25.7 28.3 25.7 28.2 25.7 28.2 25.7 28.2 25.7 28.0 25.6 28.2 25.6 28.1 25.7 28.2 25.8 28.0 25.7 28.1 25.2 27.7 25.6 28.2 25.7 28.0 25.7 28.3 25.7 28.1 25.7 28.1 25.7 28.1Pressure Drop across FGD (in H2O) Sorbent Type Sorbent Injection Rate (lb/hr)

6.88 bicarb 0 7.74 bicarb 0 7.74 bicarb 70 7.72 bicarb 125 4.18 bicarb 5 7.64 bicarb 94 7.71 bicarb 74 7.70 bicarb 74 7.71 bicarb 76 7.72 bicarb 85 7.69 bicarb 87 7.70 bicarb 76 7.66 bicarb 78 7.70 bicarb 79 7.69 bicarb 35 7.70 bicarb 0 7.72 bicarb 41 7.63 bicarb 56 7.75 bicarb 49 7.76 bicarb 45 7.73 bicarb 65 7.70 bicarb 90 7.70 bicarb 25 7.72 bicarb 33Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%)

2.5 12.8 1.6 12.8 1.6 12.8 1.5 12.8 13.0 8.8 scheduled outage 1.5 12.6 1.6 12.5 1.5 12.6 1.6 12.6 1.5 12.6 1.5 12.5 1.5 12.7 1.5 12.4 1.6 12.5 1.6 12.6 1.6 12.7 1.5 12.7 1.7 12.5 1.7 12.6 1.8 12.6 1.5 12.7 1.6 12.8 1.6 12.9 1.6 12.9