5

- i CHAPTER 5. ENGINEERING ANALYSIS

TABLE OF CONTENTS

5.1 INTRODUCTION

................................ ................................ ................................ ........... 5

- 1 5.2 METHODOLOGY OVERVIEW

................................ ................................ .................... 5

- 1 5.3 PR ODUCT CLASSES

................................ ................................ ................................ ..... 5

- 3 5.4 EFFICIENCY LEVELS AN ALYZED

................................ ................................ ............ 5

- 5 5.4.1 Baseline

................................ ................................ ................................ ................ 5

- 5 5.4.2 Intermediate Efficiency Levels

................................ ................................ ............ 5

- 6 5.4.3 Max

- tech Efficiency Levels

................................ ................................ ............... 5

- 10 5.5 TEARDOWN ANALYSIS

................................ ................................ ............................ 5

- 11 5.5.1 Selection of Units

................................ ................................ ............................... 5

- 11 5.5.2 Generation of Bill of Materials

................................ ................................ .......... 5

- 13 5.6 COST MODEL

................................ ................................ ................................ .............. 5

- 14 5.6.1 Cost Model Overview

................................ ................................ ........................ 5

- 15 5.6.2 Cost Model Assumptions

................................ ................................ ................... 5

- 16 5. 7 MANUFACTURER SELLING PRICE

................................ ................................ ........ 5

- 19 5.7.1 Manufacturer Markup

................................ ................................ ........................ 5

- 20 5.7.2 MSP in the Downstream Analyses

................................ ................................ .... 5

- 21 5.8 INDUSTRY COST

- EFFICIENCY RELATIONS HIPS

................................ ................ 5

- 21 5.9 RESULTS

................................ ................................ ................................ ...................... 5

- 21

LIST OF TABLES

Table 5.3.1: Product Classes

................................ ................................ ................................ ........ 5

- 4 Table 5.4.1: Baseline Unit FER and IFER for Residential Furnace Fans

................................ .... 5

- 6 Table 5.4.2: Inter mediate Efficiency Level Correlation between Technologies, Technology Status, and Analysis Approach

................................ ................................ ............... 5

- 7 Table 5.4.3: Reduction in FER or Standby Power for Each Efficiency Level

............................ 5

- 8 Table 5.4.4: Efficiency Levels for Furnace Fans Used in Non

- Hydronic HVAC Produc ts

........ 5

- 9 Table 5.4.5: Efficiency Levels for Hydronic Air Handler Fans (Heat/Cool)

.............................. 5

- 9 Table 5.4.6: Max

- Tech Efficiency Levels for Furnace Fans

................................ ..................... 5

- 10 Table 5.5.1: Characteristics of Representative Residential Furnaces

................................ ........ 5

- 12 Table 5.6.1: Cost Model Categories and Descriptions

................................ .............................. 5

- 15 Table 5.6.2: Purchased Furnace Fan Components

................................ ................................ ..... 5

- 17 Table 5.6.3: Factory Parameter Assumptions

................................ ................................ ............ 5

- 19 Table 5.9.1: MPC Estim ates for Design Option Approach Efficiency Level Components

...... 5

- 22 Table 5.9.2: Cost

- Efficiency Results for High

- Volume Product Class es

................................ .. 5

- 23 Table 5.9.3: Cost

- Efficiency Results for Low

- Volume Product Classes

................................ ... 5

- 235- ii LIST OF FIGURES

Figure 5.2.1: Engineering Analysis Methodology ....................................................................... 5-3 Figure 5.5.1: Example of BOM Spreadsheet ............................................................................. 5-14 Figure 5.6.1: Cost Model Methodology ..................................................................................... 5-16 Figure 5.7.1: Components of Manufacturer Selling Price ......................................................... 5-205

- 1 CHAPTER 5. ENGINEERING ANALYSIS

5.1 INTRODUCTION

The engineering analysis establishes the relationship between manufacturer selling price (MSP) and energy

- efficiency ( i.e.
, fan efficiency rating ( FER)) for the product s covered in this rulemaking. The cost

- efficiency relationship serves as the basis for subsequent cost/benefit calculations for individual customers, manufacturers, and the Nation. In determining this relationship, the U.S. Department of Energy (DOE) estimates the increase in the manufacturer selling price ( MSP ) associated with technological changes that reduce the energy consumption of the baseline mod els.

The primary inputs to the engineering analysis are data from the market and technology assessment (chapter 3 in the TSD), energy performance data from testing and publicly available product literature and research reports, input from manufacturers, b aseline specifications
, and production cost estimates developed using a cost model. The primary output of the engineering analysis is a set of cost

- efficiency relationships that represent the average incremental cost of increasing product efficiency above the baseline levels. In the subsequent markups analysis (chapter 6 in the TSD), DOE determines customer prices by applying distribution markups, sales tax, and contractor markups to the manufacturer sales prices (MSPs) developed in the engineering analysis . After applying these markups, the data serve as inputs to the energy use characterization (chapter 7 in the TSD) and the life

- cycle cost and payback period analyses (chapter 8 in the TSD).

In this chapter, DOE discusses : (1) the identification of repre sentative baseline units for each product class, (2) the methodology used to develop bill s of materials (BOMs) and MSPs, (3) the process for co nstructing the industry cost

- efficiency relationship s , and (4 ) the cost

efficiency relationship outputs

.

5.2 METHODOL OGY OVERVIEW

This section describes the analytical methodology used in the engineering analysis. In this rulemaking, DOE used an efficiency

- level approach in conjunction with a design option approach to identify incremental improvements in efficiency for each product class

. An efficiency level approach enabled DOE to identify incremental improvements in efficiency for efficiency

- improving technologies that furnace fan manufactures already incorporate in commercially

- available models

. A design option approach enabled DOE to model incremental improvements in efficiency for technologies that are not commercially available in residential furnace fan applications . In combination with these approaches, DOE u sed a cost

- assessment approach to determine the manufacturing production cost (MPC) at each efficiency level5

- 2 identified for analysis

. This methodology estimates the incremental cost of increasing product efficiency.

The cost

- assessment is based on reverse engineering data and was validated by manufacturer input. First, DOE used information gathered from manufacturers and /or data from the market and technology assessment to identify baseline units and representative models

. DOE select ed a set of units at th e baseline and higher efficiencies for teardown analysis based on this information. The baseline unit serves as a starting point for the analysis
, and the units selected for teardown analysis span a range of manufacturers, functionality
, and efficiencies f or commercially available products. DOE developed estimate s of MPC for the each of the units selected for teardown by disassembling each unit , developing a bill of materials
, and using th is information as input for a manufacturing cost model.

To determine the MSP of a unit at each efficiency level, DOE applied manufacturer markups to the MPC

. DOE used the same markups for this preliminary analysis as it did for furnaces in the direct final rule for HVAC products. 76 FR 37453 DOE derive d the man ufacturer markup for that rulemaking by evaluating publicly available industry financial data and through manufacturer feedback

. The results of the engineering analysis are a set of cost

- efficiency relationship s, in the form of MSP as a function of energy

- efficiency , for each product class. The methodology for the engineering analysis is a logical, concise, and reproducible process, as illustrated in Figure 5.2

. 1

.5

- 3 Figure 5.2

. 1 : Engineering Analysis Methodology

5.3 PRODUCT CLASSES

DOE identified nine key product classes and 12 additional product classes that DOE differentiated by product application and internal structure

. Key product classes are those representing most of the energy use associated with furnace fans

. DOE di rectly analyzed the nine key product class es. The 12 additional product classes represent significantly fewer shipments and significantly less energy use

. DOE identified two approaches to generating results for t he additional product classes. One approach is for DOE to generate unique results for each additional product class by extrapolating from key product class results

. Alternatively, DOE decided to group each non

- key product class with a key product class to which it is closely related in application a nd internal structure for the preliminary analysis . DOE assigned the engineering results of each key product class to the non

- key product classes with which it is grouped. Table 5.3

. 1 presents the 21 product classes and maps the additional product classes to the nine key product classes. Cost Model Manufacturer Markup Analysis

Cost

- Efficiency

Relationship (Efficiency vs MPC)

Engineering Manufacturer

Interviews Physical Teardown Analysis

Bills of Material (BOM) Selling Price

Efficiency Relationship (Efficiency vs MSP) Baseline unit, Efficiency levels,

Representative Products

Market and Tech Assessment (chapter 3) Screening Analysis (chapter 4) Virtual Teardown Analysis5

- 4 Table 5.3

. 1 : Product Classes Key Produc t Class Additional Product Classes Non

- W eatherized, Non

- Condensing Gas Furnace Fan (NWG

- NC) Non

- weatherized, Condensing Gas Furnace Fan (NWG

- C)

Weatherized , Non

- condensing Gas Furnace Fan (WG

- NC) **•** Weatherized , Non

- Condensing Oil Furnace Fan (WO

- NC)

**•** Weatherized Electric Furnace/Modular Blower Fan (WEF/WMB)

**•** Manufactured Home Weatherized Gas Furnace Fan (MH

- WG)

**•** Manufactured Home Weatherized Oil Furnace Fan (MH

- WO)

**•** Manufactured Home Weatherized Electric Furnace/Modular Blower Fan (MH

- WEF/WMB)

Non

- weathe rized , Non

- condensing Oil Furnace Fan (NWO

- NC) **•** Non

- Weatherized , Condensing Oil Furnace Fan (NWO

- C)

**•** Manufactured Home Non

- Weatherized Oil Furnace Fan (MH

- NWO) Electric Furnace / Modular Blower Fan (EF/MB)

Heat/Cool Hydronic Air Handler Fan (HAH

- HC) **•** Heat

- Only Hydronic Air Handler Fan (HAH

- H)

**•** Hydronic Air Handler Fan with Coil (HAH

- C)

**•** Manufactured Home Heat/Cool Hydronic Air Handler Fan (MH

- HAH

- HC)

**•** Manufactured Home Heat

- Only Hydronic Air Handler Fan (MH

- HAH

- H)

**•** Manufactured Home Hydronic Air Handler Fa n with Coil (MH

- HAH

- C) Manufactured Home Non

- Weatherized , Non

condensing Gas Furnace Fan (MH

- NWG

- NC) Manufactured Home Non

- Weatherized , Condensing Gas Furnace Fan (MH

- NWG

- C) Manufactured Home Electric Furnace/ Modular Blower Fan (MH

- EF/MB)

DOE developed new candidate standard levels for the key product classes based on the fan efficiency rating (FER) , a new energy use metric proposed in the furnace fan test procedure NOPR that DOE published on May 15, 2012. 77 FR 28674 FER represent s normalized annual
energy use

. F or furnace fans used in non

- hydronic HVAC products , FER only accounts for active

- mode energy use because standby and off mode energy use for furnace fans used in these products is accounted for in other DOE rulemaking activities

. For fu rnace fans used in hydronic air handlers, t he NOPR proposed to use the integrated fan efficiency rating (IFER) , a variation of FER that integrates active mode and standby mode energy use

. Chapter 3 of this TSD describes these rating metrics in greater detail.5

- 5 5.4 EFFICIENCY LEVELS AN ALYZED

DOE analyzed multiple efficiency levels for each product class presented in section 5.3 and estimated the manufacturer production cost ( MPC ) at those levels. The following subsections discuss efficiency levels from the baseline to maximum technologically feasible (“max

- tech”) efficiency for each product class. DOE identified the highest efficiency level by reviewing product literatu re for commercially available products and research reports that included energy performance data of prototype furnace fans

.

5.4.1 Baseline

DOE selected baseline units as reference points for each product class, against which changes resulting from potential n ew energy conservation standards could be measured. The baseline unit in each product class possesses the basic characteristics of products in that class. Typically, a baseline unit is a unit that just meets, but does not exceed current Federal energy

cons ervation standards and provides basic consumer utility. However, energy conservation standards for furnace fans do n ot exist

. As a result, DOE select ed baseline models typical of the least

- efficient furnace fans used in commercially available residential H VAC models.

DOE used the baseline units for comparison in several analyses, including the engineering analysis, life

- cycle cost (LCC) analysis, payback period (PBP) analysis, and national impacts analysis (NIA). To determine energy s avings that will result from a new energy conservation standard, DOE compared energy use at each of the higher energy efficiency levels to the energy consumption of the baseline unit. Similarly, to determine the changes in price to the

consumer that will result from a new energy conservation standard, DOE compared the price of a baseline unit to the price of a unit at each higher efficiency level.

DOE reviewed FER values that it calculated using test data and performance information from publicly

- available product literature to determine baseline FER rating s

. Table 5.4.1 presents the baseline FER for each non

- hydronic air handler produ ct class , and the baseline IFER for th e key hydronic air handler product class

. As discussed above, IFER integrates standby mode and off mode energy consumption with active mode energy consumption for those products

. Note that the baseline IFER for hydronic heating/cooling air handlers is sign ificantly lower than the baseline FER value s for the other product classes

. This is because standby mode consumption is much lower than active mode consumption

. In addition, IFER is normalized by total annual hours ( 8
, 760 hours) whereas FER is normalized b y total annual active mode operating hou rs (1,870 hours for single stage products ).5

- 6 Table 5.4

. 1 : Baseline Unit FER and IFER for Residential Furnace Fans

Product Class F ER (W/1000 cfm) IFER (W/1000 cfm) Non

- weatherized, Non

- condensing Gas Furnace Fan 380 Non

- weatherized, Condensing Gas Furnace Fan 393 Weatherized Gas Furnace Fan 3 33 Non

- Weatherized Oil Furnace Fan 333 Electric Furnace / Modular Blower Fan 3 12 Manufactured Home Non

- weatherized, Non

condensing Gas Furnace Fan 295

Manufactured Home Non

- weatherized, Condensing Gas Furnace Fan 319

Manufactured Home Electric Furnace / Modular Blower Fan 243 Hydronic Air Handler Fan (Heat/Cool) 107

I ncremental MPCs for intermediate efficiency levels are the MPCs for products representative of these levels minus the MPC of baseline products

. The baseline MPCs are based on products representative of the baseline efficiency level

. These incremental MPCs represent the added costs of efficiency

- impr oving design features incorporated into intermediate

- efficiency products that are not present in baseline efficiency units

. Throughout the analyses, the intermediate

- efficiency products are compared with baseline products, including evaluation of differenc es in MPC, installation cost , and operating costs (chapter 8).

5.4.2 Intermediate Efficiency Levels

DOE determined FER and IFER values representing the intermediate efficiency levels based on tests conducted for selected products according to the proposed DOE test procedure and on information obtained in AHRI’s product certification directories
, 1

5.9 manufacturer catalogs, and other publicly available literature. The intermediate efficiency levels are all defined by specific design opt ions used to attain them

. For each key product class , DOE analyzed multiple efficiency levels and estimated MPC s at each efficiency level. Section contains cost efficiency data for the full efficiency level range that DOE analyzed from the baseline efficiency level to the max tech efficiency level for each key product class.

DOE used a combination of an efficiency level approach and a design option approach to determine MPCs for intermediate efficiency levels for each product class. DOE used the efficiency level approach for i ntermediate efficiency levels that products can achieve by using commercially available technologies

. MPCs were determined based on revers e engineering of purchased products representing these efficiency levels. However, some of the efficiency levels
, particularly the higher efficiency levels, are based on use of pro totype technologies that are not commercially available or technologies that are commercially available but not in residential5

- 7 furnace fan applications

. For assessment of these efficiency levels, DOE used the design option approach , determining the additional cost and the additional energy savings associated with adoption of the particular technologies

. Table 5.4

. 2 lists the efficiency levels DOE considered, showing the technologies and analysis approach used for each

. Chapter 3 of this TSD i ncludes a detailed discussion of each technology option.

Table 5.4

. 2 : Intermediate Efficiency Level Correlation between Technologies, Technology Status, and Analysis Approach

Efficiency Level Design Option T echnology Status Analysis Approach 1 Improved PSC Commercialized Efficiency Level 2 Inverter

- Driven PSC Prototype* Design Option 3 X13 Commercialized Efficiency Level

4 ECM and Multi

Staging Commercialized Efficiency Level

5 (non

- hydronic

max

- tech) Premium ECM and Multi

- Staging + Backward

- Curved Impeller Prototype Design Option

Hydronic 6 Switching Mode Power Supply Commercialized, but not in Furnace Fan Products Design Option
Hydronic 7 (hydronic max

- tech) Toroidal Transformer Commercialized, but not in Furnace Fan Products Design Option

*DOE is aware that a furnace model using an inverter

- driven PSC motor was once commercially available, but no longer.
DOE finds from manufacturer feedback and its review of publically available product literature that manufacturers use similar furnace fan components and follow a similar technology path to improving efficiency across all product classes. DOE does not expect the percent reduction in FER associated with each design option, whether commercially availab le or prototype , to differ across product classes as a result

. Therefore, DOE determined average FER reductions for each efficiency level for a subset of key product classes and applied these reductions to all product classes

. DOE based the reductions in F ER associated with commercialized technologies o n measurements or publicly avail able performance information

. DOE based the FER reductions associated with prototype technologies on research reports that included performance data

. DOE then applied these FER reductions to each product class

.
Table 5.4

. 3 presents the percent FER reductions and reductions in standby power input that DOE determined each design option an d efficiency level

. DOE used these reductions to calculate all of the nominal FER values for the intermediate efficiency levels of all the key product classes

. The FER reductions for efficiency levels 1 through 4 are expressed in relation to the baseline

. DOE determined these percent reductions based on averaging the calculated reductions associated with all products for which information was available, including both5

- 8 tested products and products for which sufficient information was available in public lite rature

. The reduction in FER for the backward

- inclined blower design option used for efficiency level 5 is in relation to the previous efficiency level

. Note that this design option is described in more detail in chapter 3

. Finally, the impact of standby m ode efficiency improvements for efficiency levels 6 and 7 for hydronic air handler furnace fans are expressed in terms of standby mode power reduction.

Table 5.4

. 3 : Reduction in FER or Standby Power for Each Efficiency Level

Efficiency Level (EL) Design Option Percent Reduction in

FER from

Baseline Percent Reduction in

FER from Previous EL Reduction in Standby Power from Baseline ( Watts ) 1 Improved PSC 2%

- NA

2 Inverter

- Driven PSC 10% - NA

3 X13 45%

- NA 4 ECM 59%

- NA 5 (non

- hydronic

max

- tech) ECM + Backward

Curved Impeller - 10% NA

Hydronic 6 Switching Mode Power Supply - - 1 Hydronic 7 (hydronic max

tech) Toroidal Transformer - - 1

5.4.2.1 Intermediate Efficiency Levels for Non

- Hydronic Air Handler Fans

For all product classes except hydronic air handler fans, DOE analyzed four efficiency levels in addition to the baseline and the max

- tech. Table 5.4

. 4 show s the FER for each efficiency level within each non

- hydronic air handler fan product class.5

- 9 Table 5.4

. 4 : Efficiency Levels for Furnace Fans Used in Non

- Hydronic HVAC Products

Efficiency Level NWG

NC NWG

C MH

NWG

NC MH

NWG

C NW O

NC WG EF/MB MH

EF/MB Baseline 380 393 295 319 3 33 3 33 312 243 1 371 3 84 288 312 326 326 305 238 2 34 4 356 267 289 3 01 3 01 282 220 3 20 9 216 162 175 18 3 18 3 17 1 133 4 15 8 163 122 132 1 38 1 38 129 101 5 14 2 14 7 11 0 119 12 4 12 4 1 16 9 0.8

5.4.2.2 Intermediate Efficiency Levels for Furnace Fans used in Hydronic Air Handler Fans

F or furnace fans used in hydronic air handlers , DOE added two additional efficiency levels associated with design options that reduce standby and off mode energy consumption

. To analyze these efficiency levels
, DOE used cost and efficiency information developed in the
recent HVAC products rulemaking

— see chapter 5 of the HVAC products direct final rule TSD. a

Table 5.4

. 5 Based on detailed investigation of wiring diagrams, cont rol schematics, and images of control boards of both gas furnaces and hydronic air handlers DOE determined that standby/off mode power consumption and the potential for its reduction, are equivalent for these products

. shows the IFER for each hydronic air handler fan efficiency level.

Table 5.4

. 5 : Efficiency Levels for Hydronic Air Handler Fan s (Heat/Cool) Efficiency Level I FER (W/1000 cfm) Baseline 1 07 1 10 5 2 9 7.1 3 58.9 4 4 0.2 5 3 6.2 6 3 5.5 7

– Max

- tech 3 4.8

a The TSD for the direct final rule for HVAC products is accessible at the following website: http://www1.eere.energy.gov/buildings/appliance_standards/residential/residential_furnaces_central_ac_hp_direct_ f inal_rule_tsd.html5

- 10 5.4.3 Max

- tech Efficiency Levels

As part of the engineering analysis, DOE determined the maximum technologically feasible improvement in energy efficiency for the covered product s, as required by section 325(o) of EPCA. (42 U.S.C. 6295(o)) In the market and technology assessment (chapter 3 of this TSD), DOE conducted a survey of the market s for the covered products and their supporting research areas. The max

- tech efficiency level in each product class is based on a combination of design options that is not used in any known product on the market

. Some of the included design options are based on prototype designs

. Consequently, the max

- tech level designs identified are more efficient than the maximum technology that is commercially available.

The max

- tech levels identified for the key furna ce fan product classe s are shown in Table 5.4

. 6

. The max tech efficiency level design s for a ll of these product classes use a premium ECM motor and backward

- inclined i mpeller

. The premium ECM motor operate s at a higher RPM than a typical ECM, which is required for desirable operation when paired with a backward

- inclined impeller

. In addi tion, the premium ECM was a smaller diameter, resulting in a less

- restricted furnace fan inlet and improved efficiency

. For hydronic air handler fans, the max tech efficiency level design also includes a switching mode power supply (from efficiency level 6) and toroidal transformer in addition to a premium ECM and backward

- inclined impell er (efficiency level 5)

.

Table 5.4

. 6 : Max

- Tec h Efficiency Levels for Furnace Fans

Product Class Max

- Tech Efficiency Level FER , W/1000 cfm FER (W/1000 cfm) I FER (W/1000 cfm) Non

- weatherized, Non

- condensing Gas Furnace Fan 142 Non

- weatherized, Condensing Gas Furnace Fan 147 Weatherized Gas Furnace Fan 110 Non

- weatherized Oil Furnace Fan 119 Electric Furnace / Modular Blower Fan 124 Manufactured Home Non

- weatherized, Non

condensing Gas Furnace Fan 124

Manufactured Home Non

- weatherized, Condensing Gas Furnace Fan 116

Manufactured Home Electric Furnace / Modular Blower Fan 90.8 Hydronic Air Handler Fan (Heat/Cool) 3 4.85

- 11 5.5 TEARDOWN ANALYSIS

Other than obtaining detailed manufacturing costs directly from a manufacturer, the most accurate method for determining the production cost of a product is to disassemble it piece

- by

piece, compile a bill of materials (BOM), and estimate the material and labor cost of each component

. DOE refers to this practice as a physical teardown. A suppleme ntary method, called a catalog teardown (or “virtual teardown”) , uses published manufacturer product literature and supplementary component data to estimate the major physical differences betwee n the catalog teardown unit and a similar physical teardown unit. One alternative to the teardown method is to conduct price surveys to determine the production cost , but this approach only provides insight into total MPC under current market conditions

. T he teardown approach provides insight into MPC by component and cost category, which enables DOE to estimate product costs and prices as new energy conservation standards change the affected market

. Units selected for physical teardowns were dismantled, and each part was characterized according to weight, manufacturing processes, dimensions, material, and quantity, in order to facilitate the creation of a complete BOM and manufacturing cost estimate for the product. B OMs for catalog teardowns leverage exi sting BOMs from teardowns by substituting components that are different between models based on product literature

. These modifications are based on data taken from manufacturer specification sheets and supplementary component data.

5.5.1 Selection of Units

For the teardown analysis of furnace fans
, DOE included 26 physical teard owns and two additional virtual teardown s

. DOE identified and selected representative units across the entire range of efficiencies that are currently available to consumers. To the exte nt possible, all major efficiency levels and technologies were captured in the selection of models for teardown analysis. Each product class was considered separately.

Teardown units must be representative of the ir product class; hence their characterist ics should be representative of typical characteristics of the products sold in the market

. The characteristics of the key product classes are shown in Table 5.5.1 . DOE also required that teardown units be manufactured in considerable volume, be commonly available, and have the most popular features.5

- 12 Table 5.5

. 1 : Characteristics of Representative Residential Furnaces

Product Class Input Heat Capacity

kB tu/h Airflow Capacity cfm Heat Exchanger Type Number of Heat Exchangers Non

- weatherized, Non

- condensing Gas Furnace Fan 70 1200 Clamshell/ Tubular 1

Non

- weatherized, Condensing Gas Furnace Fan 70 1200 Clamshell/ Tubular 2

Weatherized Gas Furnace Fan 70 1200 Clamshell/ Tubular 1

Non

- weatherized Oil Furnace Fan 120 1200 Drum 1

Electric Furnace / Modular Blower Fan 70 1200 Electrical Resistance Heat Elements 1

Manufactured Home Non

weatherized, Non

- condensing Gas Furnace Fan 70 1200 Clamshell/ Tubular 1

Manufactured Home Non

weatherized, Condensing Gas Furnace Fan 70 1200 Clamshell/ Tubular 2

Manufactured Home Electric Furnace / Modular Blower Fan 70 1200 Electrical Resistance Heat Elements 1

Hydronic Air Handler Fan (Heat/Cool) 70 1200 Hydronic 1

DOE also adopted more specific criteria to guide the selection process. In order to understand incremental manufacturing costs associated with design options that improv e efficiency, products chosen for teardowns included models of various efficiency levels taken from the same manufacturer and product series to the extent possible. This approach minimized the cost effects of non

- efficiency

- related desig n differences between models. The manufacturers that were chosen have large market shares of the particular product class. DOE made an exception to this criterion for the highest efficiency product (or max

- tech product) in each product class; as such, the max

- tech products for teardown were chosen irrespective of manufacturer. DOE selected products to represent max

- tech efficiency that include design options that have the highest potential for energy savings according to interested party feedback on the fra mework document

. This approach was necessary because FER ratings were not available

. DOE also selected products that minimized the occurrence of non

- efficiency

- related premium features, which could inflate the incremental manufacturing cost of achieving higher

efficiency levels.5

- 13 DOE surveyed the residential furnace fan industry and identified products available to

consu mers as well as prototypes developed by research efforts. DOE then applied the aforementioned criteria and selected baseline, intermediate, and max

- tech units that were as close to the representative characteristics as possible and included the most preval ent technologies on the market.

Because the large majority of residential furnace fan shipments fall into the non

weatherized gas product class, DOE focused its teardown analysis heavily on non

- weatherized
gas furnace fans . As a result, DOE selected un its for teardown that include nine non

- weatherized
, non

- condensing gas furnace fans and three non

- weatherized , condensing gas furnace fans

. DOE selected the remainder of the unit s for teardown from the remaining key product classes

. The furnace fans selected spanned the range of efficiency levels from baseline to max

- tech

. DOE also selected units for teardown with airflow capacities above and below the representative 1,200 cfm

. DOE did not identify the model number or manufacturer of the units examined during the teardown analysis because this could expose sensitive information about individual manufacturers’ products.

5.5.2 Generation of Bill of Materials

The end result of each teardown i s a structured BOM, describing each product component and its relationship to the other parts in the estimated order in which manufacturers assembled them. The BOMs describe each fabrication and assembly operation in detail, including the type of equipment needed for fabrication ( e.g. , presses, drills) and the process cycle times. The result is a thorough and explicit model of the production process. The BOMs incorporate all materials, components, and fasteners classified as either raw materials or purchase d parts and assemblies. The classification into raw materials or purchased parts is based on DOE’s previous industry experience, recent information in trade publications, and discussions with high

- and low

- volume original equipment manufacturers (OEMs). DO E also visited several manufacturing plants (for this rulemaking and other rulemakings that cover the HVAC products in which furnace fans are used) to reinforce its understanding of the industry’s current manufacturing practices. For purchased parts, the purchase price is an estimate based on high

- volume price quotations and detailed discussions with suppliers and manufacturers . For fabricated parts, the price of intermediate materials ( e.g. , tube, sheet metal) and the cost of transforming them into finished parts is an estimate based on current industry pricing. For a continued discussion of the cost details and assumptions, refer to section 5.6.2

. The BOM for a catalog teardown is identically structured and provides a description in equal detail to the BOM of a physical teardown

. However, it is generated using a slightly different methodology

. BOMs for catalog teardowns are generated by modifying the BOM of a similar unit that has been physically torn down

. These modifications reflect the major physical differences between the units

. Specific to this engineering analysis, the catalog teardown methodology was employed to generate bills of materials for fans with inverter

- driven PSC5

- 14 motors and fans with backward

- inclined impellers . DOE physically tore down five fans with improved PSC motors and n ine fans with ECM motors

. Based on these physical teardowns, DOE executed one supplementary PSC with inverter catalog teardown and one supplementary ECM with a backward

- inclined impeller catalog teardowns

. Figure 5.5

. 1 below shows an example of a section of a BOM spreadsheet. Each row of the spreadsheet represents a single part of the unit assembly and includes a description of the part, a material type, initial and final dimensions, and weight. These rows also include placeholders for the type and number or duration of fabrication processes (stamping, drilling, etc.) required to create that part. From this information, a part cost is generated, and the part costs are summed across the sheet to create a cost estimate for the entire unit.

Figure 5.5

. 1 : Example of BOM Spreadsheet

5.6 COST MODEL

The cost model is a detailed, component

- focused, activity

- based tool for estimating the manufacturing cost of a product. Once teardo wn s were completed
, DOE implement ed a cost model that could translate the physical information from the BOMs into manufacturing costs. The cost model is based on production activities and divides factory costs into materials, labor
, depreciation, and overh ead

. DOE defines the cost inputs of these broader categories in Table 5.6.1

.5

- 15 Table 5.6

. 1 : Cost Model Categories and Descriptions Major Category Sub

- Category Description

Material Costs Direct Raw materials ( e.g

. , coils of sheet metal) and purchased parts ( e.g

. , fan motors, compressors )

Indirect Material used during manufacturing ( e.g. , w elding rods, die oil, release media )

Manufacturing Labor Assembly Part/ unit assembly on manufacturing line

Fabrication Conversion of raw material into parts ready for assembly

Indirect Fraction of overall labor not associated dire ctly with product manufacturing ( e.g

. , forklift drivers, quality control ) Supervisory Fraction of indirect labor that is paid a higher wage

Depreciation Equipment, Conveyor, Building Straight line depreciation over expected life

Tooling Cost is allocated on a per

- use basis or obsolescence, whichever is shorter

Other Overhead Utilities A fixed fraction of all material costs meant to cover electricity and other utility costs Maintenance Based on installed equipment and tooling investment Property Tax and Insurance A fixed fraction based on total unit costs

DOE entered the cost data from all the BOMs

— whether they were obtained through physical teardowns or catalog teardowns

— into the cost model. The cost model analysis created cost estimates for each of the products analyzed in the teardown analysis. The cost model uses

s pecific assumptions to provide cost estimates ; the following sections describe these assumptions.

5.6.1 Cost Model Overview

This section provides a general overview of the process by which the cost model converts the physical information in each product’s BOM in to cost information. After gathering component information through physical teardowns and organizing it into BOMs, the resulting data were used as inputs for the cost model spreadsheet. To determine the costs, DOE follow ed one of two different paths, depen ding on whether a subassembly was purchased (out

- sourced) or produced in

- house. For purchased parts, DOE gathered price quotations from major suppliers at different production volumes. For parts produced in

- house, DOE reconstructed manufacturing
processes for each part using modeling software based on internal expertise. For example, for an access panel, DOE deduced the time required for setup, handling, changeover, and punching holes, as well as the number of holes and hits. By repeating this process, DOE was able to assign labor time, equipment utilization, and other important factors to each subassembly in each of the5

- 16 units considered for this analysis. The last step was to convert the information into dollar values. To perform this task, DOE collected in formation on such factors as labor rates, tooling depreciation, and costs of purchased raw materials. DOE assumed values for these parameters using internal expertise and confidential information available to its contractors. Figure 5 .6

. 1 provides an illustration of the cost model methodology.

Figure 5.6

. 1 : Cost Model Methodology

In sum, DOE assigned costs of labor, materials, and overhead to each part, including coils, whether purchased or produced in

- house. DOE then aggregated single

- p art costs into major assemblies

. Furnace fans are a component of HVAC products that include other products not associated with the cost or efficiency of the furnace fan

. Therefore, DOE limited the scope of its engineering analys is to the components that comprise the furnace fan assembly, including :

**•** fan motor and integrated controls;

**•** primary control board;

**•** impeller;

**•** fan housing; and

**•** components used to direct or guide airflow.

DOE summarized these costs in a spreadsheet. DOE repea ted this same process for each unit in the engineering analysis, representing a specific efficiency level at the chosen capacity and mapped the resulting c ost

- efficiency points to use as a basis for developing the cost

- efficiency relationship s.

5.6.2 C ost Model Assumptions

Assumptions about manufacturer practices and cost structure play an important role in estimating the final cost of the products. DOE used assumptions regarding the manufacturing process parameters, ( e.g. , equipment use, labor rates, tooling depreciation, and cost of purchased raw materials ) to determine the value of each component. It then summed the values of the components into assembly costs and, finally, the tota l MPC for the product. The MPC includes Purchased Parts Bill of Materials Fabrication Processes Assembly Processes Teardown Observatio n Production Cost Raw Materials Finished Materials5

- 1 7 the material, labor, depreciation, an d overhead costs associated with the manufacturing facility. The material costs include both raw materials and purchased part costs. The labor costs include fabrication, assembly, and indirect and overhead (burdened) labor rates. The depreciation costs inc lude equipment depreciation, tooling depreciation, and building depreciation. The overhead costs include indirect process costs, utilities, equipment and building maintenance, and rework

. The following sections describe the cost model assumptions related t o material prices, purchased parts and factory parameters.

5.6.2.1 Material Prices

DOE determined the cost of raw materials by using prices for copper, steel, and aluminum from the American Metals Market. 2 DOE noted that there have been drastic fluctuations in me tal prices over the last few years. To account for these large fluctuations, DOE used prices of metals that reflect a five

- year average of the Bureau of Labor Statistics Producer Price Indices (PPIs) spanning 200 6 to 20 11

. 3

5.6.2.2 Fabricated Parts and Purchased Parts

DOE characterized parts based on whether manufacturers fab ricated them in

- house or purchas ed them from outside suppliers. For fabricated parts, DOE estimated the price of intermediate materials ( e.g. , tube, sheet metal) and the cost of forming them into finished parts. For purchased parts, DOE estimated the purchase price for OEMs based on discussions with the manufacturers. Whenever possible, DOE obtained price quotes directly from suppliers of the manufacturers of the units being analyzed. DOE assu med that the components in Table 5.6

. 2 were purchased from outside suppliers.

Table 5.6

. 2 : Purchased Furnace Fan Components Assembly Purchased Sub

- Assemblies

Fan Assembly Fan Motor Motor Capacitor Impeller

Controls Transformer PCB

V ariability in the costs of purchased parts can account for large changes in the overall MPC values calculated. The purchased part prices utilized in this study were typical values based on estimated production volume s and other factors. In actuality
, p urchased part costs can vary significantly based on the quantities desired and the component suppliers chosen . The role of purcha se part prices in the MPC calculation is further magnified because these parts comprise significant portions of these systems by cost. Additi onally, some parts, such as molded plastic components, may be produced in

- house by some manufacturers and purchased by others. The choice between these options would result in changes to the calculated overall system costs.5

- 18 The market for HVAC products is highly segmented, as described in chapter 3. S ome products like non

- weatherized gas furnaces are produced at volum es significantly larger than other products under review. In addition, s ome manufacturers offer most types of the HVAC products included in this rule, while other manufacturers focus on niches. DOE separated furnace fan product classes into high

- volume product classes and low

- volume product classes t o account for these factors, which contribute to manufacturers’ purchasing power and ultimately, purchased part prices. DOE categorized furnace fans used in oil furnaces and hydronic air ha ndlers as low

volum e products. DOE categorized all other product classes as high

- volume products. Based on feedback from manufacturers, DOE has made estimates regarding the cost of acquiring purchased parts as a function of the manufacturing volume. High

- volume manufacturers operating also in lower

- volume adjacent markets are expected to have purchased part price efficiencies consistent with their higher overall purchasing volume from their suppliers

.

5.6.2.3 Factory Parameters

Certain factory parameters, such as fabrication rates, labor rates
, and wages
, also affect the cost of each unit produced

. DOE factory parameter estimates were based on internal expertise and manufacturer feedback

. Table 5.6.3 below lists the factory parameter assumptions used in the cost model. T hese factory parameters are independent of the efficiency level of the unit produced

. DOE recognizes that the current production levels of high

- efficiency units may be a small fraction of the current total production
, but under a standard, the production levels of these units could rise to baseline levels. As stated in the previous section, DOE divided furnace fan manufacturers into high

- volume manufacturers and low

- volume manufacturers. The factory parameters shown below are only representative of high

- volume manufacturing

. Low

- volume operations (i.e., oil furnace and hydronic air handler production) would show mu ch lower manufacturing volumes and fewer shifts per da y, among other factors

.5

- 19 Table 5.6

. 3 : Factory Parameter Assumptions

Parameter Furnace Fan Estimate Actual Annual Production Volume (units/year) 1,250,000 Work Days Per Year (days) 250 Assembly Shifts Per Day (shifts) 2 Fabrication Shifts Per Day (shifts) 2 Fabrication Labor Wages ($ /h ) 16 Assembly Labor Wages ($ /h ) 16 Length of Shift (hrs) 8 Average Equipment Installation Cost (% of purchase price) 10% Fringe Benefits Ratio 50% Indirect to Direct Labor Ratio 33% Average Scrap Recovery Value 30% Building Cost ($/ft 2 ) 202 Worker Downtime 10 % Building Life (in years) 25 Burdened Assembly Labor Wage ($ /h ) 24 Burdened Fabrication Labor Wage ($ /h ) 24 Supervisor Span (workers/supervisor) 25 Supervisor Wage Premium (over fabrication and assembly wage) 30%

*Includes non

- weatherized mobile home fur naces.

5.7 MANUFACTURER SELLING PRICE

The output of the cost model is the MPC , which includes all direct costs including production

- related labor, materials, depreciation
, and overhead costs (as defined in section 5.6 )

. To obtain the MSP, DOE multiplies the MPC by the manufacturer markup. The MSP includes all production and non

- production costs as well as profit

. The markup includes sales, general and admi nistrative, research and development, other corporate expenses
, and profit. The components of MSP are shown in Figure 5.7

. 1

. The MPCs are obtained as an output of the cost model, and the manufacturer markup costs were derived as described in section 5.7.1 below.5

- 20 Figure 5.7

. 1 : Components of Manufacturer Selling Price

5.7.1 Manufacturer Markup

In the preliminary analysis
, DOE used the manufacturer markups that DOE developed for the HVAC products final rule

. The methodology DOE used to determine manufacturer markup for the HVAC product s final rule is included in chapter 5 of the HVAC products direct final rule TSD. 4

In the engineering analyses for residential furnaces and CAC and heat pump products, DOE also included shipping costs in the MSP

. DOE included shipping costs in the CAC engineering analysis because implementation of certain design options involved increas ing the size and weight of the product, which increases shipping costs

. DOE also inclu ded shipping costs in the furnace rulemaking to be consistent with the CAC rulemaking , even though no size increases were considered for furnaces

. DOE did not include shipping costs in the MSP for its engineering a nalysis of furnace fans because, a s discus sed in detail in chapter 4 of this TSD, DOE did not consider design options that would impact the size of the HVAC product

. T he manufacturer marku p varied by product class. DOE used a markup of 1.35 for product classes including HVAC products designed for site

- built homes and 1.30 for product cla sses including HVAC products designed for manufactured home s

. These values are equivalent to those used by DOE in the recent direct final rule analysis for HVAC products. Manufacturer Selling Price

Full Cost of

Product

Manufacturer Production Cost

Direct Labor Direct Material Overhead

Indirect Labor

Indirect Material

Maintenance

Depreciation

Taxes

Insurance related
to assets Non

- Production Cost

Selling

Market Research

Advertising

POS Promotion

Salesperson Comp & Travel

Logistics (Warehousing, Delivery, Record

Keeping, Order

Processing) General & Admin.

Costs of Service & Staff Units

General Corporate

Costs (Comp, etc) R & D

Costs associated with finding new

and improved

products or
processes

Code Compliance

Modernization Interest

Cost of borrowing

funds Profit5

- 21 Consequently, DOE does not expect use of the design options identified in this rulemaking to impact shipping costs

.

5.7.2 MSP in the Downstream Analyses

The MSPs derived in the engineering analysis are important inputs to the life

- cycle cost analysis (LCC) and the manufacturer impact analysis (MIA). In the LCC, the MSPs are necessary to calculate the total installed cost of each unit. I n the MIA, DOE constructs a number of scenarios that analyze how different pricing schemes impact manufacturers financially. In the MIA, both MSP and the direct production cost components of MSP are important drivers of results. DOE discusses how the engin eering analysis is used in the other analyses in chapters 8 and 12 of the TSD

.

5.8 I NDUSTRY COST

- EFFICIENCY RELATIONSHIPS

For residential furnace fans , DOE used the cost model to estimate the MPC of various products across the full range of efficiencies and f or many manufacturer s with significant market share. DOE used these results as the basis for its cost

- efficiency relationship for all furnace fan product classes.

DOE began its construction of the cost efficiency relationship at the baseline efficiency lev el. To create an industry average cost at the baseline efficiency, DOE calcul ated a market

weighted average of the cost modeling results for each product that was torn down at the baseline efficiency level. DOE then calculated the market weighted average i ncremental increase in cost
to achieve each efficiency level above the baseline for each level analyzed up to max

- tech

. DOE developed one cost

- efficiency relationship for high

- volume product classes and another for low

- volume product classes

. DOE found that MPC did not differ significantly across product classes at a given efficiency level and production volume because manufacturers use similar components. Therefore, DOE assigned on set of MPC s across each efficiency level for all high

- volume p rod uct classes and another set of MPCs across each efficiency level for all low

volume product classes.

5.9 RESULTS

The final result of the engineering analysis is a set of cost

- efficiency relationship s . DOE developed relationship s for the nine key product classes of furnace fans using the analysis methodology described above. The c ost

- efficiency results are shown in Table 5.9

. 2 and Table 5 .9

. 3 in the form of FER or IFER versus MPC for high

- volume product classes and low

- volume product classes, respectively

. The MPC presented is not for the entire HVAC product because furnac e fans are a component of the HVAC product in which they are integrated

. The presented5

- 22 MPC includes costs only for the components of the HVAC product that impact FER or IFER, which DOE considered to be the:

**•** fan motor and integrated controls;

**•** primary contr ol board;

**•** impeller;

**•** fan housing; and

**•** components used to direct or guide airflow.

Table 5.9.1 presents MPC estimates of the design option components for efficiency levels established using the catalog teardown / design option approach

. As stated previously, DOE used the design option approach to estimate the cost and efficiency impacts for technologies that are not commercially available in furnace fan applications

.

Table 5.9

. 1 : MPC Estimates for Design Option Approach Efficiency Level Co mponents Efficiency Level Design Option High Volume MPC Low Volume MPC

2 Inverter Controls for Inverter

Driven PSC $11.52 $16.24

5 Premium ECM and Multi

- Staging + Backward

- Curved Impeller $107.02 $122.01

6 Switching Mode Power Supply NA* $7.25 7 Toroidal Transformer NA* $10.95 * Standby mode consumption is not covered in this rulemaking for high volume products; therefore the standby design options are not applicable to high volume product classes.
For efficiency level 2, the MPC represents the cost of an inverter , $11.52 and $16.24 for high volume and low volume products, respectively

. DOE estimated this cost by reverse engineering an inverter that is suitable for use in furnace fan applications

. The MPC for efficiency level 5 includes the cost for a premium ECM motor and the cost of a backward

- curved impeller

. DOE used a 10% markup on the estimated MPC for an ECM as the added cost for a premium ECM
motor

. DOE found that prototype designs using backward

- curved impellers re quire ECM motors with pr emium characteristics that increase the cost of the motor , such as higher RPM capabilities and a smaller outer diameter

. DOE used photographs and specifications found in research reports
to determined cost model inputs , such as weight and fabrication proce sses, to estimate the MPC of the b ackward

- curved impeller to be $12 .00 and $12.32 for high volume and low volume products, respectively

. The MPC estimates for efficiency levels 6 and 7 are the same as those used in the direct final rule engineering analysi s for HVAC products.

As stated above, DOE used the cost

- efficiency curves from the engineering analysis as an input to the life

- cycle cost (LCC) analysis to determine the added price of the more efficient furnace fan components in HVAC equipment sold to th e custo mer (see chapter 8 of the TSD).5

- 23 Table 5.9

. 2 and Table 5.9

. 3 present the MPC and efficiency metric (FER or IFER) for each of the key product classes. As discussed in section 5.3
, DOE assigned the engineering analysis results of each key product class to the additional product classes with which it is grouped (see Table 5.3

. 1 )

.

Table 5.9

. 2 : Cost

- Efficiency Results for High

- Volume Product Classes

Efficiency Level Baseline EL1 EL2 EL3 EL4 EL5

Design Option Improved PSC PSC + Inverter X13 ECM +Multi

- Stage Premium ECM + Multi

- Stage +

BI Impeller
MPC $68.98 $70.98 $80.50 $91.71 $160.93 $176.00
NWG

- NC 380 371 344 209 158 142 NWG

- C 393 384 356 216 163 147
MH

- NWG

- NC 295 288 267 162 122 110
MH

- NWG

- C 319 312 289 175 132 119 WG 333 326 301 183 138 124 EF/MB 312 305 282 171 129 116
MH

- EF/MB 243 238 220 133 101 90.8

Table 5.9

. 3 : Cost

- Efficiency Results for Low

- Volume Product Classes Efficiency

Level Baseline EL1 EL2 EL3 EL4 EL5 EL6 EL7

Design Option Improved PSC PSC + Inverter X13 ECM +Multi

Stage Premium ECM + Multi

Stage +

BI Impeller Switch Mode PS Toroidal XFMR

MPC $84.34 $91.32 $100.58 $121.59 $190.96 $206.35 $213.60 $224.55 O

- NC 333 326 301 183 138 124 NA NA HAH

- HC 107 105 97.1 58.9 40.2 36.2 35.5 34.85

- 24 REFERENCES

1 AHRI. Directory of Certified Product Performance , Performance Data Updated June 7, 2010. Last accessed June 7, 2010. <http://www.ahridirectory.org/ahridirectory/pages/home.aspx>

2 American Metals Market, (Last accessed December 8, 2010.) < http://www.amm.com/ .>

3 U.S. Department of Labor, Bureau of Labor Statistics, Producer Price Indices . (Last accessed December 8, 2010.) < http://www.bls.gov/ppi/ >

4 U.S. Depar tment of Energy, Building Technologies Program, Residential Furnaces and Central Air Conditioners and Heat Pumps Direct Final Rule Technical Support Document

. < http://www1.eere.energy.gov/buildings/appliance_standards/residential/residential_furnaces_ central_ac_hp_direct_final_rule_tsd.html >